Product nameMultifunctional centralized meter reading board (for meters with com. function, indoor spec.)Model

ＫＩＬＶＩＳ－ＨＡ５Ｆ （HA0F,HA1F,HA5F）

Document

Product Specifications

Azbil Kimmon Co., Ltd,

Document number
KM-KILVIS-HA-011

Re.
6

＜ Table of Contents＞

１．Summary ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・ １
１．１ Overview of Equipment and Functions ・・・・・・・・・・・・・・・・・・・・・・・・・・・
１
１．２ Compatible Meter ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・ ２
２．Strong point・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・
２
３．Metering board configuration ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・
３
４．System Configuration Example ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・
３
４．１ Star configuration ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・４
４．２ Bus configuration ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・
４
４．３ Mixed star/bus configuration ・・・・・・・・・・・・・・・・・・・・・・・・・５
５．Technical specification・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・
６

５．１ Centralized meter reading board main unit ・・・・・・・・・・・・・・・・・・・・・・・・・・
６
５．２ Meter with communication function ・・・・・・・・・・・・・・・・・・・・・・・・・・・・
８
５．３ Terminal equipment ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・
９
６．Outline Drawing ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・ １０

１．Summary
The multifunctional centralized meter reading panel "KILVIS-HA" is a device that performs
centralized meter reading for meters installed in dispersed locations in tenant buildings,condominiums, and other housing complexes. It can be used both as a high-level device and as aterminal device for data collection connected to a PC.
There are two types of connection methods: the star method, in which the signal line from themeter is connected directly to the meter reading board, and the bus method, in which the signal
line is connected via a terminal device. The meter to be connected is the pulse output type.

1.1 Overview of Equipment and Functions(1) Meter reader

The meter reading is displayed by operating the buttons on the operation panel.
The built-in printer type can perform printing process.
It also has the following external interfaces①USB: Connects to a PC for setup and data collection.
②RS232C: Connects to a PC for setting and data collection.
③Line A: Automatic meter reading is performed via an 8-bit KHK-compliant common-type
NCU or an NCU for PHS lines.
It has four expansion slots and can house up to four star or bus boards.
(Only one bus board can be installed)(2) Star board

Star boards for pulse meters count pulses.
Up to 32 meters can be connected to each star board.
(3) Bus substrate

Built-in interface board for connecting external terminal equipment. It supplies power to theterminal equipment.
When using a bus board (when using a terminal device), the maximum number of star boards is three.
(4) Terminal equipment

The terminal device counts pulses.
The terminal device for the pulse meter is connected to the bus board of the centralized meterreading board and can connect up to 16 meters per line.
Up to 16 meters can be connected per terminal unit.

1<KM-KILVIS-HA-013_7>

1.2 Compatible Meter(1) Meters with communication function

・Electronic water meter
・Gas meter with communication function (microcomputer III, general-purpose, commercial use)
・Other devices employing similar communication methods (battery-powered electromagnetic, etc.)

２．Strong point
1) Up to 1,280 meters can be read, making it possible to accommodate tenants, condominiums, and other buildings.
2) Both star and bus systems are supported for meter connections.
Furthermore, the star and bus systems can be mixed, making it easy to add more meters.
3) The main body of the meter reader has four expansion slots, which can accommodate up to four busboards (interface board for terminal equipment) and four star boards (interface board for pulse).
(Only one bus board can be installed)

4) The centralized meter reading board can display and print not only totaled values but also alarms, etc.
5) Energy monitoring of gas and water is possible with a meter with communication function.
6) The distance from the centralized meter reading panel to the terminal equipment can be as long as 1 km.
7) The distance between the centralized meter reading panel or terminal unit and the meter can berelatively long, up to 200 meters.
8) The terminal block for meter connection uses a one-touch connection terminal block, allowing wiringwithout the use of crimp terminals.
9) One dedicated pushbutton is assigned to the function used for meter reading, making operation easy.
10) Data from the centralized meter reading board can be obtained with dedicated software for personalcomputers.
(For details, please refer to the specifications of the dedicated software.)11) The enclosure is designed for indoor use.

2<KM-KILVIS-HA-013_7>

３．Centralized meter reading board configuration
The configuration of this centralized meter reading board is shown below.
(1) Centralized inspection panel
・It consists of an operation panel, power supply unit, interface board, etc.
・The operation panel consists of red 7-segment LEDs and pushbutton switches for function selection,etc.
(2) Bus board

Built-in interface board for use with terminal equipment.
・Power is supplied to the terminal equipment from the centralized meter reading panel through thetransmission line. (No totalization operation is performed in the event of power failure.)
・Transmission line connections can be up to 5 lines, with a maximum of 16 terminal devices per line.
・When all 5 lines are used, the maximum number of terminal devices is 80.
However, one of the five lines is shared with the slot for the star board in the main body of the meter reading board.
For this common line, one star board (for 32 units) is equivalent to two terminals (16 units x 2).
(3) Star board

By integrating the star board into the meter reading board, the meter can be connected directly tothe centralized meter reading board.
・The star board can connect up to 32 pulse meters (2-wire).
(4) Terminal equipment

・The terminal device totalizes the pulses from the meter and transmits them to the centralized
meter reading panel.
・Up to 16 pulse meters (2-wire) can be connected to the terminal unit.

(5)Meter with communication function
・Data acquisition is performed by communication using the communication cable of themeter's A line.

3<KM-KILVIS-HA-013_7>

４．System Configuration Example
4.1 Star configuration
Up to four star boards can be built in without using bus boards.

M・• Max32 台
・
M

集

スター基板
中・
検••・・・

メーター接続最大数
4×32=128 台

針盤

M・• Max32 台・M

スター基板

Configuration Max. 4 star boards, Max. 128 meters

4.2 Bus configuration
Up to 80 terminal devices can be used by incorporating a bus board.

集Terminal

Bus board
中・
検針
盤

M

Terminal

Max16units････ M

M

・････
Max
16 unitsMax
16 units

M・・・・Max
Terminal

5 LineM

Terminal

Max16units････ M

Maximum number of meters connected 5 x 16 x 16M････
Max
16 unitsMax
16 unitsM= 1,280(5 x 14 x 16 = 1,120 units if meterreading is done via PC communication, etc.)

Configuration 1 bus board, max. 80 terminals, max. 1,280 meters
4<KM-KILVIS-HA-013_7>

4.3 Mixed star/bus configuration
In the case of mixed star-bus system, bus boards are used, so up to three star boards can be built in.

Bus board

Terminal・M・

Terminal････ M

端末装置(Note 1) (Max5lines)

M針Max
16 units

・・・・
検 4 lines

････M

Max
16 units

端末装置

Max16 台････ MMMMax
16 units････
Max
16 units

メー

Maximum number of meter connections

4x16x16 = 1,024 unitsM(4 x 14 x 16 = 896 units when meterreading is done by computer communication,etc.)

Star board
Max3 units

M・・ Max32 units
・M

Maximum number ofmeters connected
3 x 32 = 96 units

Configuration 1 bus board, max. 3 star boards
Bus system section: Maximum of 1,024 meters (when 4 lines are used instead of the 5 linesof Note 1)
Star system section: Maximum of 96 meters(Note 1)
There are a total of five bus board lines.
When all five lines are used, one line is shared with the slot for the star board in themain body of the meter reading board. For this common line, one star board (for 32 units)
is equivalent to two terminal units (16 units x 2).
The same is true for the other two lines.

5<KM-KILVIS-HA-013_7>

５．Technical specification
5.1

Centralized meter reading board main unit
KILVIS-HA0F（For water），KILVIS-HA1F（for gas）
KILVIS-HA1F（for both water and gas）

Model name

Number of connectedterminals and meters

Host device andconnection port
CalendarsclocksandStar method (4 boards)：bus system： 80 Terminal

Mixed bus/star (1 board)：

0 Terminal

78 Terminal

128 Meters
1,280 Meters※１
1,280 Meters※１

Mixed bus/star (2 boards)： 76 Terminal

1,280 Meters※１

Mixed bus star (3 boards)： 74 Terminal

1,280 Meters※１

USB（USB-RS232C conversion port）
RS232CA line (8-bit telegram communication line)［Entity code: S4, meters correspond to W2 and G2 guideline values only］

Year, month, day, hour, minuteFeatureAll "Confirmation" can be done in two types: all units anddesignated room numbers. The built-in printer can also print.

① Pointer value

Reads the "pointer value" of all meters.

② hourly meter reading

The meter stores all meter readings at preset times (regularmeter readings) and reads these regular meter readings.

③ Confirmation of fuse registration

Check the "fuse registration" on the gas meter.

④Safety Continuity Confirmation

What to check depends on the type of gas meter. (※２)

⑤ Instantaneous flow rate value confirmation(※２)

Check the "instantaneous flow value" of the water meter. (※２)

⑥Confirmation of leakage volume Check the "leakage volume" of the water meter.

(※２)

Check the "leak time" of the water meter.

(※２)⑧Excessive flow check Check the "leak time" of the water meter.

(※２)⑦ Leakage time confirmation⑨ Other

Maintenance functions for the meter reading board are available.

Display

Red 7-segment LED x 15 digits, Red LED x 23

①Block No.

Numerals 2 digits (red 7-segment LED x 2)

② Room No.

Numerals 5 digits (red 7-segment LED x 5)

③ Pointer value

Numeric 8 digits (decimal point position shifts depending on caliber)

Other display contents vary depending on the mode.

④Alarm contents

3 types, others (red LED x 4)

⑤ Unitm3・m3/hPrinting (built-in printer)

Thermal serial dot system (paper width 58 mm), 32 characters per line

① Block No.

Numeric 2 digits② Room No.

Numeric 5 digits③Current guideline value

Numeric 8 digits (decimal point position shifts depending on caliber)④ Alarm display

Battery voltage drop, leakage/leakage, overload/pressure, other⑤ Unitm3・m3/hOtherPrinting will vary depending on other operations.

※１：When communicating via PC, etc., a maximum of 1,120 meters can be connected.
※２：Please refer to the meter's function manual for details.
<KM-KILVIS-HA-013_7>
6

Operation key① Pointer key

water metergas meter

Guideline value confirmation

Guideline value confirmation②On-time meter reading key Regular meter reading confirmation

Regular meter reading confirmation③Function 1 key（※３）

Confirmation of fuse registration④Function 2 key（※３）

Instantaneous flow rate value confirmation

Confirmation of leakage volume Safety Continuity Time Confirmation⑤Function 3 key（※３）

Leakage time confirmation

None⑥Function 4 key（※３）

Overdosage checkNone⑦Up arrow key

Advance the room number by one.

⑧down arrow key

Move the room number back by one.

⑨Meter Selection

Select the type of meter.
(Water meter, Gas meter, Electricity meter, Other )⑩Manual/Automatic switching key

Select manual/automatic meter reading.

⑪print key

Selects whether to print or not. (Enabled when the printer option is selected.)⑫alarm printing

Selects normal or detailed alarm printing.

⑬execution key

Perform meter reading, etc.

⑭Power key

Turns the power supply ON/OFF.

Printer

Thermal line dot method
Thermal paper model: P-58-30

Power supply

AC100V±10% ， 50/60HzPower consumption

Max. 12VA (main unit only)

Installation method

Indoor specifications (wall mounting) 400(W)×400(H)mm

Waterproof Structure

IP grade IPX4

Ambient temperature-10°C to +50°C (0°C or higher for printers)

Ambient humidity

85%RH or less (no condensation)

Installation Location

Locations where there is little dust and humidity, and where there is norisk of indoor gas retention without direct sunlight. In addition, pleasetake into consideration that the display may be difficult to read in aplace exposed to direct sunlight. Please consider these points.

External dimensions

450(W)×450(H)×150(D)mm (excluding protruding parts)

Enclosure Material

steel plate

Paint color

Japan Paint Manufacturers Association No. 22-90B (equivalent to 2.5Y9/1, beige type)

WeightIndoor spec. approx. 20kg

Supply voltage toterminal equipment

24 VAC (supplied from centralized meter reading board)

terminal equipment transmission 4-wire shieldline cable
Transmission distance(between board andterminal)

About 1ｋｍ

※３：For water-only and gas-only, the item name of the function is the name of the exclusive use.
7

<KM-KILVIS-HA-013_7>

5.2

Meter with communication function(1) Common specifications for meters with communication function

input signal

8-bit communication system for automatic meter reading

Setup switch

With addressable switch

Monitor L E D

Communication monitor LED

Distance between meters

VCTF 0.5mm2 or more(2 wires) Max. 200m

(2) Star board (for meters with communication function)

Number of meters connected

Max. 32 units

Power supply

Supplied from centralized meter reading board DC5V

Power consumption

Max. 0.5VA

5.3

Terminal equipment (for meters with communication function)

Model name

ＫＩＬＶＩＳ－ＨＡＴ１

Number of meters connected

Max. 16 units

Terminal-to-terminaltransfer line cable

4-wire shield

Power consumption

Supplied from centralized meter reading panel 24 VAC(signal line: DC signal)

Power consumption

Max.0.6VA

External dimensions

201(W)×274(H)×52(D)mm

Case Color

Light gray (Munsell 5Y-7.5/1 equivalent)

Waterproof Structure

IP grade IPX3

Installation Location

WeightA place with little dust and humidity, outof direct sunlight, and where there is nodanger of gas accumulation.
About 1kg8

<KM-KILVIS-HA-013_7>

６．Outline Drawing(1）Body

Unit：ｍｍ4504002560

33060

1945360

45

19150
2931182540450400

2525803.2(2)Terminal

201

348.5

4.5

269
273.5

Product name seal

289.5

(161)

4-φ12 mounting holes

Push

10

<KM-KILVIS-HA-013_7>