Grundfos.book Page 1 Monday, May 23, 2011 10:17 AM

GRUNDFOS INSTRUCTIONS

MQInstallation and operating instructions

CUSGrundfos.book Page 2 Monday, May 23, 2011 10:17 AM

LIMITED WARRANTY
Products manufactured by GRUNDFOS PUMPS CORPORATION (Grundfos) arewarranted to the original user only to be free of defects in material and workmanshipfor a period of 24 months from date of installation, but not more than 30 months fromdate of manufacture. Grundfos' liability under this warranty shall be limited to repairing or replacing at Grundfos' option, without charge, F.O.B. Grundfos' factory or
authorized service station, any product of Grundfos' manufacture. Grundfos will not
be liable for any costs of removal, installation, transportation, or any other charges
which may arise in connection with a warranty claim. Products which are sold but
not manufactured by Grundfos are subject to the warranty provided by the manufacturer of said products and not by Grundfos' warranty. Grundfos will not be liablefor damage or wear to products caused by abnormal operating conditions, accident,
abuse, misuse, unauthorized alteration or repair, or if the product was not installedin accordance with Grundfos' printed installation and operating instructions.
To obtain service under this warranty, the defective product must be returned to the
distributor or dealer of Grundfos' products from which it was purchased together
with proof of purchase and installation date, failure date, and supporting installation
data. Unless otherwise provided, the distributor or dealer will contact Grundfos oran authorized service station for instructions. Any defective product to be returned
to Grundfos or a service station must be sent freight prepaid; documentation supporting the warranty claim and/or a Return Material Authorization must be included
if so instructed.
GRUNDFOS WILL NOT BE LIABLE FOR ANY INCIDENTAL OR CONSEQUENTIAL DAMAGES, LOSSES, OR EXPENSES ARISING FROM INSTALLATION,
USE, OR ANY OTHER CAUSES. THERE ARE NO EXPRESS OR IMPLIED WARRANTIES, INCLUDING MERCHANTABILITY OR FITNESS FOR A PARTICULARPURPOSE, WHICH EXTEND BEYOND THOSE WARRANTIES DESCRIBED OR
REFERRED TO ABOVE.
Some jurisdictions do not allow the exclusion or limitation of incidental or consequential damages and some jurisdictions do not allow limit actions on how long
implied warranties may last. Therefore, the above limitations or exclusions may not
apply to you. This warranty gives you specific legal rights and you may also haveother rights which vary from jurisdiction to jurisdiction.

2

Contents

Grundfos.book Page 3 Monday, May 23, 2011 10:17 AM

MQ
English (US)Installation and operating instructions . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .4
Español (MX)Instrucciones de instalación y funcionamiento. . . . . . . . . . . . . . . . . . . . . . . . . .23
Français (CA)
Notice d'installation et de fonctionnement . . . . . . . . . . . . . . . . . . . . . . . . . . . . .43
Appendix . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .62

3

Grundfos.book Page 4 Monday, May 23, 2011 10:17 AM

English (US)English (US) Installation and operating instructions
CONTENTSWARNINGPage

1.

Introduction2.

Items supplied

3.

Symbols used in this document

4.
4.1

Applications
Pumped liquids

5.
5.1

Identification
Type key

6.
6.1

Operating conditions
Suction lift

7.
7.1
7.2
7.3
7.4
7.5

Mechanical installation
LocationFoundation
Space requirement
Pipework
Protective cover

8.
8.1
8.2
8.3
8.4
8.5

Electrical connection
Generator or inverter
Wiring diagram
Winding resistance measurement
Winding resistance measurement
Start-up

9.
9.1
9.2

FunctionsControl panel
Pump stop

10.
10.1
10.2

Maintenance
Service kits
Start-up after a long period of inactivity

11.

Service

12.
12.1
12.2
12.3

Technical data
Dimensions
Electrical data
Approvals

13.

Accessories

14.

Fault finding chart

15.

MQ frequently asked questions

16.

Disposal

4

4
4
5
5
5
6
6
7
7
8
8
8
8
8
10
11
11
12
12
13
14
15
15
16
17
17
17
17
18
18
18
18
18
19
21
22

Prior to installation, read these
installation and operating instructions. Installation and operationmust comply with local regulations and accepted codes of goodpractice.

1. Introduction
The MQ is a low-noise water supply system
consisting of pump, motor, pressure tank andcontroller combined into one compact unit.
The system is suitable for both indoor and outdoor use.
The self-priming pump starts automaticallywhen water is consumed in the installation andstops when consumption ceases. The internal,built-in non-return valve prevents backflow
during priming and operation.
The MQ pump incorporates overtemperatureand dry-running protection as well as a userfriendly control panel.
The built-in pressure tank reduces the numberof starts and stops in case of leakage in the
installation.

2. Items supplied
The MQ packaging contains these items:•

MQ water supply system with built-in nonreturn valve•

non-return inlet valve in plastic bag•

installation and operating instructions.

Grundfos.book Page 5 Monday, May 23, 2011 10:17 AM

English (US)

3. Symbols used in this document

WARNING
If these safety instructions are notobserved, it may result in personal
injury!
CautionIf these safety instructions are notobserved, it may result in malfunction or damage to the equipment!

Note

Notes or instructions that makethe job easier and ensure safe
operation.

4. Applications
The MQ water supply system is designed forthese typical applications:•water pressure boosting(maximum inlet pressure: 40 psi)•

water supply from wells (maximum suction
lift: 25 ft), for example– in private homes– on farms– in market gardens and other large gardens.

The pump is suitable for rain water.

4.1 Pumped liquids
Thin, clean, non-aggressive liquids, not containing solid particles or fibres.

5

Grundfos.book Page 6 Monday, May 23, 2011 10:17 AM

5.1 Type key
ExampleMQ

3 -35 A -O -A BVBPPump type
Nominal flow rate [m³/h]
Head [m]Code for pump version
A: Standard
Code for pipework connection
Code for materials
A: Standard
Code for shaft seal

Protective cover(accessory)

Pressuretank coverControl panel
Discharge port
Priming plug

Suctionport

End-coverplug

Drain plug
Base plate

Fig. 1

6

MQ water supply system. Protective cover is required for outdoor use.

TM04 3648 4908

English (US)

5. Identification

Grundfos.book Page 7 Monday, May 23, 2011 10:17 AM

MQ 3-35
Maximum flow rate [gpm]Maximum pressure [psi]Maximum system pressure [psi]MQ 3-45
22

51

65
108

Maximum suction lift [ft]; see page 62

25

Minimum ambient temperature [°F]/[°C]32/0Maximum ambient temperature [°F]/[°C]

113/45

Minimum liquid temperature [°F]/[°C]32/0Maximum liquid temperature [°F]/[°C]95/35

Net weight [lbs]29Sound pressure level [dB(A)]< 70

Tank volume [oz]English (US)

6. Operating conditions

13.5

Air pressure in tank [psi]22 to 25

Connections

1" NPT

Priming and drain plugs

3/8" GAS

6.1 Suction lift
The maximum suction lift of the pump can be
determined from the diagram, page 62.
Example:If the suction lift is 10 ft, the length of the suction pipe must not exceed 72 ft.

7

Grundfos.book Page 8 Monday, May 23, 2011 10:17 AM

7.3 Space requirement

7.1 Location

For inspection and service, allow a minimum
clearance of 60" behind the pump.

The pump is suitable for indoor and outdoor
installation. It is resistant to sunlight.

Note

Should the unlikely event of aninternal leakage occur, pumped
liquid will be drained out from thebase and/or end cover instead ofdamaging the pump. Install thepump in such a way that no undesirable collateral damage canarise.

60"
TM04 3746 5008

Note

For outdoor installation, the pumpmust be fitted with a protective
cover (accessory). See section
7.5 Protective cover and
13. Accessories.

Fig. 3

Being self-cooling, the pump requires nospace or ventilation at the sides.

Note

7.2 Foundation
Mount the pump on the base plate with horizontal suction port and vertical discharge port.

Minimum clearance behind thepump

Ensure that the maximum ambient
temperatures do not exceed thevalues stated in section
6. Operating conditions.

7.4 Pipework

The pump must be installed horizontally.
The maximum permissible inclination angle is± 18 °. See fig. 2.

Note

Never use unnecessary force
when connecting the pipes.

The pump is supplied with 1" NPT screwed
connections. Fit the connections in the suction
and discharge ports. See fig. 4. The pump discharge port is flexible, ± 5 °, to facilitate the fitting.

Max. ± 18 °Horizontal installation of the MQ

To prevent movement and vibrations, thepump and base plate can be secured to a solid
foundation by means of the bolt holes in thebase plate. For pipework connection, see section 7.4 Pipework.

8

TM01 9698 2600

Fig. 2

TM01 9691 2600

English (US)

7. Mechanical installation

Fig. 4Fitting of screwed connections insuction and discharge ports

TM04 4271 1009

Carefully screw the discharge connection into
the discharge port, using a spanner or similar
tool. Hold the discharge connection, andtighten the pump discharge union nut with yourhand. See fig. 5.

Fig. 5

Correct: Tighten the discharge
union nut with your hand

7.4.3 Long suction pipes
A separate non-return inlet valve is suppliedwith the pump. In case of long suction pipes,
we recommend to fit the non-return inlet valve
in the pump suction port. See section
7.4.4 Fitting of the non-return inlet valve
The pipes must be adequately supported oneither side of the pump to avoid straining thepump connections.
7.4.4 Fitting of the non-return inlet valve
The non-return inlet valve reduces the risk oflosing pump priming in negative suction applications and improves the auto-aspiration
capability, for example in water supply from acistern.

TM 044272 1009

Install the non-return inlet valve as follows,
see fig. 8:

Fig. 6

1. Remove the suction connection of thepump.
2. Fit the non-return inlet valve into the suction port in the direction shown in fig. 8.
3. Refit the pump connection.

Wrong: Do not use a tool to tighten
the discharge union nut
Note

7.4.1 Suction pipes connected to a well

Foot valve

Fig. 7TM01 9693 2600

If the pump draws water from a well, we recommend to fit a foot valve to the end of thesuction pipe. See fig. 7.

Applications with positive inlet
pressure do not require installation of the non-return inlet valve,
due to the fact that the MQ pumpincorporates an internal nonreturn valve at the discharge side.

Suction pipes connected to a well

7.4.2 Suction hose instead of pipe
TM 04 4121 0809

If a suction hose is used instead of a pipe, thehose should not exceed the lengths stated in
the graph, page 62. The suction hose must be
minimum Ø1". The hose must be of the noncollapsible type.

Fig. 8Fitting of non-return inlet valve

9

English (US)Grundfos.book Page 9 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 10 Monday, May 23, 2011 10:17 AM

Note

Failure to use the protective coverin outdoor installations will invalidate the warranty.

The protective cover protects the control panel
against the weather. It is available as anaccessory. See section 13. Accessories.
To fit the protective cover, click the cover onto
the top of the control panel so that it engages
with the top cooling ribs.
To remove the cover, pull the two clips outwards, free of the cooling ribs, and pull thecover upwards.

TM04 3745 5008

English (US)

7.5 Protective coverFig. 910

Protective cover8. Electrical connection
The electrical connections and additional protection should be carried out by qualified persons in accordance with local regulations.

The pump must be connected to the mains via
a sheathed cable with a protective groundlead. It is possible to replace the mains supply
cable. See fig. 10.

WARNING
Non-submersible pump.

Never make any connections in
the pump terminal box unless theelectricity supply has beenswitched off for at least 5 minutes.
Risk of electric shock:This pump is supplied with agrounding conductor and grounding type attachment plug.
To reduce the risk of electric
shock, install only on circuit protected by a Ground-Fault-CircuitInterrupter (GFCI).

TM01 9694 2600

If the power cord is damaged, it
must be replaced by the manufacturer, an authorized service centeror by a qualified person in order toavoid risks.

Fig. 10 Electrical connection
Connect the mains supply cable of the pumpto the electricity supply. When the cable isconnected, a red and a green indicator light on
the control panel will be on. See fig. 11.

TM01 9695 2600

This pump is not intended, nor has
it been investigated for use inswimming pool or marine areas.
This pump has been evaluated foruse with water only.
Do not start the pump until it has
been filled with water (primed, seefig. 12).
Acceptable for indoor and outdooruse.

Fig. 11 Connection of mains supply cable

8.1 Generator or inverter

Enclosure type 3.
The operating voltage and frequency aremarked on the nameplate. Make sure that the
motor is suitable for the electricity supply on
which it will be used.

Note

The MQ can be powered by a generator or an inverter. However, thepump will only operate satisfactorily if the generator or inverter
generates a true sinusoidal wave
with the necessary power and voltage input. The generator must be
sized 10 % above the P1(input power) of the pump. For P1,
see section 12.1 Dimensions.

11

English (US)Grundfos.book Page 11 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 12 Monday, May 23, 2011 10:17 AM

Electric motorC

Red (main)
Black

YellowWhite

Yellow

Capacitor

8.2.1 115 V

Yellow

Yellow/green (ground)Black (phase)> CableWhite (neutral)
OrangeBlack
Red> Flow sensor> Pressure switch

B A

TM02 2424 4708

English (US)

8.2 Wiring diagram

Fig. 12 Wiring diagram - 115 V

8.3 Winding resistance measurement
Motor[V/Hz]

Measuring point

Winding

Resistance[± 10 %]115/60A-B (black - red)A-C (black - white)

Main
Aux

1.4
5.5

Ambient temperature
[°F]

[°C]

70

21

The measurement can be done with or without cables connected to the PCB and the capacitor.

12

Grundfos.book Page 13 Monday, May 23, 2011 10:17 AM

Blue

YellowWhite

Yellow

Electric motor

Yellow

Capacitor

English (US)8.3.1 230 V

Yellow/green (ground)Black (phase)> CableWhite (neutral)
OrangeBlack
Red> Flow sensor> Pressure switch

TM02 2424 2409

B A

Fig. 13 Wiring diagram - 230 V

8.4 Winding resistance measurement
Motor[V/Hz]

Measuring point

230/60A-B (blue - red)A-C (blue - white)

Winding
Main
Aux

Resistance[± 10 %]5.4
5.4

Ambient temperature
[°F]

[°C]

70

21

The measurement can be done with or without cables connected to the PCB and the capacitor.

13

Grundfos.book Page 14 Monday, May 23, 2011 10:17 AM

Before start-up, the pump must be filled with
1.2 to 1.5 gallons of water to enable it to selfprime, see fig. 14. The pump is self-primingwith a maximum suction lift of 25 ft.

TM01 9696 2600

English (US)

8.5 Start-up

Fig. 14 Priming the pump
When started, the pump begins to self-prime.
When it has been primed, the pump will automatically change over to normal operation.
If the priming has not been completed within
5 minutes, the pump will stop automaticallyand attempt to restart after 30 minutes. It is
possible to reset the pump manually, see point
2 in the table of section 9.1 Control panel.

14

Grundfos.book Page 15 Monday, May 23, 2011 10:17 AM

English (US)9. Functions
9.1 Control panel

TM01 9684 2600

The MQ pump is operated entirely by meansof the control panel. See fig. 1. The control
panel offers the possibility of starting/stopping
the pump. The pump settings and operating
condition are indicated by indicator lights.
See fig. 15.

Fig. 15 Control panel
The functions of the control panel are described in the table below:
Illustration

Description

1

Indicator light (red)When the indicator light is on, the pump is on standby.

2

On/Off button
The pump is started/stopped by means of the on/off
button.
The on/off button can also be used for manual resetting in case of an alarm condition:•

3

press once for resetting and• press once more for starting.
Indicator light (green)
Indicates that the pump is ready for operation.
When the indicator light is on, the pump will start automatically when water is consumed. The pump will stopa few seconds after the water consumption has
ceased.

15

Grundfos.book Page 16 Monday, May 23, 2011 10:17 AM

English (US)4

Pump on (green)
The indicator light is on when the pump is running.

5

Auto reset (green)
As standard, this function is activated on delivery.
•

When the indicator light is on, the auto-reset function is activated. The pump will automaticallyattempt to restart every 30 minutes after an alarm/fault over a period of 24 hours. After this period,
the pump will remain in the alarm condition.

•

When the indicator light is off, the auto-reset function is deactivated. The pump will not restart afteran alarm/fault.

The auto-reset function can be activated/deactivatedby pressing the on/off button for 5 seconds.
Note: When water is consumed, the pump will startand stop automatically, whether the auto-reset light ison or off.
Alarm (red)6

The indicator light is on when the pump is in alarm
condition.
The alarm condition may have been caused by:•

dry running•

overtemperature•overloaded motor•

seized-up motor/pump.

See section 9.2 Pump stop.

9.2 Pump stop
The pump incorporates an electronic protective function that will stop the pump in case of•

dry running•

overtemperature•overloaded motor•

seized-up motor/pump.

The pump will restart automatically after
30 minutes (for 24 hours) in case of any typeof fault if the auto-reset function is activated(the green indicator light on the control panel
is on, see point 5 in the table of section
9.1 Control panel).

Note

16

The pump settings are stored.
After supply failure, the pump willautomatically revert to its previous
operating condition when the electricity supply is reconnected.

10. Maintenance
Under normal operating conditions, the pumpis maintenance-free. However, it is recommended to keep the pump clean.

WARNING
Do not remove the pressure tankfrom the pump unless it has been
vented through the air escapevalve.

10.2 Start-up after a long period ofinactivity
The end cover incorporates a plug which canbe removed by means of a suitable tool.
See fig. 17. It is then possible to free the pumprotor if it has seized up as a result of inactivity.
If it has been drained, the pump must be filledwith liquid before start-up. See fig. 14.

Never touch the electronics unlessthe pump has been switched off
for at least 5 minutes.

TM04 3633 4608

If there is any risk of frost damage, drain thepump through the drain hole and slacken theunion nut on the discharge pipe, see fig. 16.
The pump must be filled with liquid before it isstarted up again. See fig. 14.

TM01 9697 4403

Fig. 17 Removing the end-cover plug

Fig. 16 Draining the pump

10.1 Service kits
Service kits are available for the MQ pump.
The service kits consist of the following
replaceable parts:•

shaft seal

•

motor

•

electronic units•

hydraulic components.

11. Service
Note

If a pump has been used for a liquid that is injurious to health or
toxic, the pump will be classified
as contaminated.

If Grundfos is requested to service the pump,
Grundfos must be contacted with details about
the pumped liquid, etc. before the pump isreturned for service. Otherwise Grundfos canrefuse to accept the pump for service.
Possible costs of returning the pump are paidby the customer.
However, any application for service (no matter to whom it may be made) must include
details about the pumped liquid if the pumphas been used for liquids which are injurious
to health or toxic.

17

English (US)Grundfos.book Page 17 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 18 Monday, May 23, 2011 10:17 AM

12.1 Dimensions

TM01 9799 508

English (US)

12. Technical data

12.2 Electrical data
MQ 3-35

MQ 3-45

Enclosure type3

Enclosure class

IP 54

Insulation class

B

Supply cable

6.56 ft SJTW 18 awg
with/without plug

Voltage,power consumption,
P1 [W]

1 x 115-120 V – 10/+ 6 %,60 Hz

900 W/8.0 A

1100 W/10.0 A

1 x 220-240 V – 10/+ 6 %,60 Hz

850/4.0 A

1050/4.8 A

12.3 Approvals
UL-listed and CSA-approved.

13. Accessories
Model

Designation

MQ 3-35 / MQ 3-45

Protective cover

18

Product number
96590745

Grundfos.book Page 19 Monday, May 23, 2011 10:17 AM

Fault

Cause

1. The pump does a) Insufficient water.
not start.

English (US)14. Fault finding chart
RemedyCheck the water supply/suction
pipe.

b) Overheating due to excessive
liquid temperature(above +95 °F/+35 °C).

Supply cold liquid to the pump.

c) Overheating due to seized-up/
choked-up pump.

Contact your pump supplier.

d) Too low or too high supply volt- Check the supply voltage and corage.
rect the fault, if possible.
e) No electricity supply.

Connect the electricity supply.

f)Open a tap. Check that the height
between the top point of the discharge pipe and the pump does notexceed 50 ft.

No water consumption.

g) Shaft is blocked.

Rotate the shaft as described in 10.2h) Pump is in alarm condition.

Reset the pump by means of the on/off button. See point 2 in the table ofsection 9.1 Control panel.

2. The pump does a) Existing pipework is leaking or
not stop.
defective.

3. The pump cuts
out during
operation.

Repair the pipework.

b) Non-return valve is blocked or
missing.

Clean the valve or fit a new nonreturn valve.

a) Dry running.

Check the water supply/
suction pipe.

b) Overheating due to excessive
liquid temperature(above +95 °F/+35 °C).

Supply cold liquid to the pump.

c) Overheating caused by:– high ambient temperature(> 113 °F/45 °C)

Contact your pump supplier.

– overloaded motor– seized-up motor/pump.
d) Too low supply voltage.

Check the supply voltage and correct the fault, if possible.

4. The pumpstarts andstops too frequently.

a) Leakage in suction pipe or air
in water.

Check the water and the supply/suction pipe.

b) Too low or too high pressure inpressure tank.

Check the pressure in the pressuretank. See section 6. Operating conditions.

5. The pumpgives electric
shocks.

a) Defective ground connection.

Connect the ground connection to
the pump in accordance with local
regulations.

19Grundfos.book Page 20 Monday, May 23, 2011 10:17 AM

English (US)

Fault

Cause

Remedy6. The pumpstarts when nowater is consumed.

a) Internal non-return valve is
defective, or the existing pipework is leaking or defective.

Clean the valve or fit a new one.

If the pump does not start when the fault has been corrected, contact your pump supplier orGrundfos for further information.

20

15. MQ frequently asked questions
1. What causes the MQ to start?
Answer: The MQ is equipped with both aninternal flow switch and pressure switch.
Each of these can turn the MQ on, depending on water consumption. The pump will
start when:
The flow rate is greater than 0.3 gpm
OR
the pressure is below 29 psi.
2. What causes the MQ to stop?
Answer: Other than the manual on/off button, only the flow switch is authorized toautomatically stop the MQ during normal
operation when flow drops below 0.3 gpm.
The pump will shut off in 12-15 seconds
after flow stops.
Additionally, the MQ will be turned off in theevent of a dry-run or overtemperature
alarm.
3. What is the maximum height of a tap
above the MQ?
Answer: If a tap or faucet is installed atheights greater than 50 ft above the MQ,
there is the potential risk that the MQ will
never start. In cases where the MQ starts
due to low pressure (low flow rates), thepressure has to fall below the pressure
switch activation point (28-30 psi factory
setting). To allow for the pressure of 50 ft ofwater, tolerances and a safety margin, we
recommend a maximum height of 50 ft
between the MQ and any tap.

5. How is the dry-run condition determined?
Answer: The dry-run alarm is declared
when the motor is running AND the flowrate is less than 1.6 gpm AND when pressure is less than the pressure switch setting. When this condition lasts for 12 seconds, the alarm will be declared after
1 minute, and the motor is stopped.
The MQ attempts to automatically restart
every 30 minutes for a maximum of
24 hours. If more than 24 hours pass without water, the pump must be restarted manually.
6. What is the maximum inlet pressure
allowed in the MQ?
Answer: For both MQ 3-35 and MQ 3-45,
the maximum internal pressure allowed is
109 psi. The maximum inlet pressure when
added to the MQ pressure must not exceed
109 psi.
Remember that inlet pressure adds to the
MQ pressure, so with a 40 psi inlet pressure supplied to the MQ 3-45, internal pressures can reach approximately 105 psi(65 + 40 psi).
Additionally, if inlet pressures exceed thebuilt-in pressure switch activation point(28-30 psi factory setting), the pressure
switch will be unable to activate, and theability to turn the MQ on at low flow rates
will be lost. In this situation, only the flow
switch will be able to turn the MQ on at flow
rates above its activation point of 0.3 gpm
7. What is the priming capacity of the MQ?

4. What is the purpose of the built-in pressure tank?

Answer: Approx. 1.2 gallons.

Answer: The built-in pressure tank comesfrom the factory, pressurized at approximately 23 psi (with the pump pressure atzero) and holds a volume of 14 ounces ofwater. It is designed to minimize motor
startup due to small leaks.

21

English (US)Grundfos.book Page 21 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 22 Monday, May 23, 2011 10:17 AM

English (US)8. How is overload temperature/overtemperature of the MQ detected?
Answer: The motor has a thermal switch
incorporated in the motor windings.
The switch will cut out the motor and startagain. See the table below.
Thermal protection[V]
Cut-out
Cut-in

[°F]

[°C]

115

302

150

230

275

135

Both

151

65-67

9. Where can a pressure gauge be easily
installed to measure the discharge pressure?
Answer: In the discharge piping or in 3/8"
GAS straight thread opening used to add
priming water to the pump.

16. Disposal
This product or parts of it must be disposed ofin an environmentally sound way:
1. Use the public or private waste collection
service.
2. If this is not possible, contact the nearest
Grundfos company or service workshop.

Subject to alterations.
22Español (MX) Instrucciones de instalación y funcionamientoÍNDICE

ADVERTENCIA
Página1.

Introducción2.

Artículos suministrados

3.

Símbolos utilizados en este
documento

4.
4.1

Aplicaciones
Líquidos bombeados

5.
5.1

Identificación
Nomenclatura

6.
6.1

Condiciones de funcionamiento
Altura de succión

7.
7.1
7.2
7.3
7.4
7.5

Instalación mecánica
Ubicación
Cimentación
Requisitos de espacio
Tuberías
Cubierta protectora

8.
8.1
8.2
8.3
8.4
8.5

Conexión eléctrica
Generador o inversor
Diagrama de cableado
Medida de la resistencia de bobinado
Medida de la resistencia de bobinado
Puesta en marcha

9.
9.1
9.2

Funciones
Panel de control
Paro de la bomba

10.
10.1
10.2

Mantenimiento
Kits de mantenimiento
Puesta en marcha tras un periodo
prolongado de inactividad

11.

Mantenimiento

12.
12.1
12.2
12.3

Datos técnicos
Dimensiones
Datos eléctricos
Homologaciones

13.

Accesorios

14.

Tabla de búsqueda de averías

15.

Preguntas frecuentes acerca de labomba MQ

16.

Eliminación

Antes de llevar a cabo la instalación, lea estas instrucciones deinstalación y funcionamiento.
La instalación y el funcionamiento de la bomba deben satisfacer los requisitos de la normativa
local vigente y los códigos aceptados de buenas prácticas.

23
23
24
24
24
25
25
26
26
27
27
27
27
27
29
30
30
31
31
32
33
34
34
36
37
37
37
37
38
38
38
38
38
39
41
42

1. Introducción
La bomba MQ es un sistema de suministro deagua con bajo nivel de emisión de ruidos compuesto por un motor, un recipiente a presión yun regulador, todo ello combinado en una unidad de tamaño compacto. El sistema es apto
para el uso interior y exterior.
La bomba autocebante se pone automáticamente en marcha cuando se consume agua
en la instalación, y se detiene cuando cesa el
consumo. La válvula de retención, interna e
integrada, evita el reflujo durante el cebado yel funcionamiento de la bomba.
La bomba MQ está dotada de protección contra exceso de temperatura y funcionamiento
en seco, así como de un sencillo panel decontrol.
El recipiente a presión integrado reduce elnúmero de arranques y paros en caso de que
exista una fuga en la instalación.

2. Artículos suministrados
El paquete de la bomba MQ contiene lossiguientes artículos:•

sistema de suministro de agua MQ con válvula de retención integrada•

válvula de retención de entrada en bolsade plástico•

instrucciones de instalación y funcionamiento.

23

Español (MX)Grundfos.book Page 23 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 24 Monday, May 23, 2011 10:17 AM

Español (MX)

3. Símbolos utilizados en este
documento

ADVERTENCIA
Si no se respetan estas instrucciones de seguridad podrían producirse lesiones personales.

Precaución

Si no se respetan estas instrucciones de seguridad podrían producirse problemas o daños en elequipo.

Nota

Notas o instrucciones que facilitan
el trabajo y garantizan un funcionamiento seguro.

4. Aplicaciones
El sistema de suministro de agua MQ ha sido
diseñado para cumplir los requisitos de lassiguientes aplicaciones típicas.
•

aumento de la presión de agua(presión máxima de entrada: 40 psi)•suministro de agua desde pozos (altura
máxima de succión: 25 ft), por ejemplo– en hogares privados– en granjas– en huertas y jardines grandes de otros
tipos.

La bomba es apta para bombear aguas pluviales.

4.1 Líquidos bombeados
líquidos de baja densidad, no agresivos, que
no contengan partículas o fibras sólidas.

24

Grundfos.book Page 25 Monday, May 23, 2011 10:17 AM

Español (MX)

5. Identificación
5.1 Nomenclatura
EjemploMQ

3 -35 A -O -A BVBP

Tipo de bomba
Caudal nominal [m³/h]
Altura [m]Código de versión de la bomba
A: Estándar
Código de conexión a tubería
Código de materiales
A: Estándar
Código del sello de flecha

Cubierta protectora(accesorio)

Panel de control

Cubierta deldepósito a presión

Puerto de descarga
Tapón de cebado

Tapón dedrenajeFig. 1

Tapón dela cubierta
posterior

Plataforma de base

TM04 3648 4908

Puerto desucción

Sistema de suministro de agua MQ. Se requiere una cubierta protectora para el uso
en exteriores

25

Grundfos.book Page 26 Monday, May 23, 2011 10:17 AM

Español (MX)6. Condiciones de funcionamiento
MQ 3-35
Caudal máximo [gpm]Presión máxima [psi]MQ 3-4522

51

65

Presión máxima del sistema [psi]108

Altura máxima de succión [ft];consulte la página 49

25

Temperatura ambiente mínima [°F]/[°C]32/0

Temperatura ambiente máxima [°F]/[°C]

113/45Temperatura mínima del líquido [°F]/[°C]32/0

Temperatura máxima del líquido [°F]/[°C]95/35

Peso neto [lbs]29

Nivel de presión sonora [dB(A)]< 70

Volumen del depósito [oz]13,5Presión de aire en el depósito [psi]Conexiones
Tapones de cebado y drenaje

6.1 Altura de succión
La altura máxima de succión de la bomba sepuede determinar haciendo uso del gráfico
que se encuentra en la página 49.
Ejemplo:
Si la altura de succión es de 10 ft, la longitud
del tubo de succión no deberá superar los
72 ft.

26

22 a 25
1" NPTGAS de 3/8"

7. Instalación mecánica

7.3 Requisitos de espacio

La bomba es apta para su instalación enentornos interiores y exteriores. Resiste la luz
solar directa.

Nota

Si desea instalar la bomba en un
entorno exterior, deberá equiparlacon una cubierta protectora (accesorio). Consulte las secciones
7.5 Cubierta protectora y
13. Accesorios.

Nota

En el caso improbable de que se
produzca una fuga interna, el
líquido bombeado se drenará de labase y/o la cubierta posterior paraevitar que la bomba resultedañada. Instale la bomba de tal
modo que no puedan surgir daños
colaterales no deseados.

Monte la bomba sobre la plataforma de basecon el puerto de succión en posición horizontal y el puerto de descarga en posición vertical.
La bomba debe instalarse en posición horizontal.

Fig. 3

Asegúrese de que las temperaturas ambiente máximas no superan
los valores indicados en la sección 6. Condiciones de funcionamiento.

7.4 Tuberías
Nota

No aplique demasiada fuerzadurante la conexión a las tuberías.

La bomba cuenta con conexiones roscadas de1" NPT. Realice las conexiones en los puertos
de succión y descarga. Consulte la fig. 4.
El puerto de descarga de la bomba es flexible(± 5 °), lo cual facilita la conexión.

TM01 9698 2600

Instalación horizontal de la bomba
MQ

A fin de evitar movimientos y vibraciones, labomba y la plataforma de base pueden fijarse
a un cimiento sólido por medio de los orificios
de sujeción de la base. Si desea obtener más
información acerca de la conexión de labomba al sistema de tuberías, consulte la sección 7.4 Tuberías.

Espacio mínimo tras la bomba

Al disponer de un sistema de autorrefrigeración, la bomba no requiere espacio ni ventilación en los laterales.

TM01 9691 2600

El ángulo máximo de inclinación admisible esde ± 18 °.
Consulte la fig. 2.

Fig. 260"

Nota

7.2 Cimentación

Máx. ± 18 °A fin de permitir la realización de operaciones
de inspección y mantenimiento, debe mantenerse un espacio mínimo de 60" tras labomba.

TM04 3746 5008

7.1 UbicaciónFig. 4

Instalación de las conexiones roscadas en los puertos de succión ydescarga

27

Español (MX)Grundfos.book Page 27 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 28 Monday, May 23, 2011 10:17 AM

TM04 4271 1009

Fig. 5

Correcto: Apriete la tuerca de uniónde descarga con la mano

7.4.2 Uso de una manguera de succión enlugar de un tubo
Si se utiliza una manguera de succión enlugar de un tubo, la manguera no deberá
superar las longitudes indicadas en el gráfico
de la página 49. La manguera de succióndebe tener un diámetro mínimo de Ø1".
La manguera debe ser de tipo no plegable.
7.4.3 Tubos de succión largos
La bomba incluye una válvula de retención deentrada independiente. Si se utilizan tubos desucción de gran longitud, se recomienda instalar la válvula de retención de entrada en elpuerto de succión de la bomba. Consulte lasección 7.4.4 Instalación de la válvula deretención de entrada

TM 044272 1009

Los tubos deben apoyarse debidamente a
cualquier lado de la bomba para evitar forzar
sus conexiones.

Fig. 6

Incorrecto: No utilice una herramienta para apretar la tuerca deunión de descarga

7.4.1 Tubos de succión conectados a unpozo
Si la bomba extrae agua de un pozo, se recomienda instalar una válvula de pie en el
extremo del tubo de succión.
Consulte la fig. 7.

Válvulade pieFig. 728

TM01 9693 2600

Español (MX)Enrosque con cuidado la conexión de descarga en el puerto de descarga utilizando una
llave fija o herramienta similar. Sostenga laconexión de descarga y apriete la tuerca deunión de descarga de la bomba con la mano.
Consulte la fig. 5.

Tubos de succión conectados a unpozo

7.4.4 Instalación de la válvula de retención
de entrada
La válvula de retención de entrada reduce elriesgo de pérdidas de cebado de la bomba en
aplicaciones de succión negativa y mejora lacapacidad de autosucción, por ejemplo al
suministrar agua desde una cisterna.
Instale la válvula de retención de entrada de lasiguiente manera, consulte la fig. 8:
1. Retire la conexión de succión de la bomba.
2. Instale la válvula de retención de entrada
en el puerto de succión, en la dirección que
se indica en la fig. 8.
3. Vuelva a instalar la conexión de la bomba.

Nota

La garantía quedará invalidada sino se usa la cubierta protectora en
una instalación exterior.

La cubierta protectora protege el panel decontrol contra las inclemencias climatológicas.
Se encuentra disponible como accesorio.
Consulte la sección 13. Accesorios.
Para instalar la cubierta protectora, encájela
en la parte superior del panel de control demodo que quede sujeta por los bordes disipadores.
Para quitar la cubierta, tire de las dos sujeciones hacia fuera, sepárela de los bordes disipadores y tire de ella hacia arriba.

TM04 3745 5008

Nota

Las aplicaciones con presión deentrada positiva no requieren la
instalación de una válvula retención de entrada debido al hechode que la bomba MQ incorpora
una válvula de retención interna
en el lado de descarga.

7.5 Cubierta protectora

Cubierta protectora

TM 04 4121 0809

Fig. 9Fig. 8Instalación de una válvula deretención de entrada

29

Español (MX)Grundfos.book Page 29 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 30 Monday, May 23, 2011 10:17 AM

TM01 9694 2600

Las conexiones eléctricas y la instalación deprotecciones adicionales deben ser llevadas acabo por personas debidamente cualificadasde acuerdo con las normas locales.

ADVERTENCIA
Esta bomba no es sumergible.
Si el cordón de alimentación es
dañado, éste debe sustituirse por
el fabricante, por su agente de servicio autorizado o por personal
calificado con el fin de evitar un
peligro.
No realice ninguna conexión en el
cuadro de terminales a menos quese haya mantenido desconectada
la fuente de alimentación eléctrica
durante al menos 5 minutos.

Fig. 10 Conexión eléctrica
Conecte el cable de alimentación de la bombaa la fuente de alimentación eléctrica. Al conectar el cable se iluminarán dos indicadores en
el panel de control, uno en color rojo y otro encolor verde.
Consulte la fig. 11.

Riesgo de descarga eléctrica:
Esta bomba está equipada con un
conductor de masa y un enchufecon conexión a masa. A fin de
reducir el riesgo de descarga eléctrica, realice la instalación únicamente en circuitos protegidos por
un interruptor de circuito de fallosde conexión a tierra (GFCI).
Esta bomba no está destinada al
uso en piscinas o áreas marítimas
ni ha sido desarrollada para ello.
Esta bomba ha sido evaluada parasu uso exclusivo con agua.

TM01 9695 2600

Español (MX)8. Conexión eléctrica

Fig. 11 Conexión del cable de alimentación
eléctrica

8.1 Generador o inversor

No ponga la bomba en marcha
hasta que se haya llenado de agua
(cebado, consulte la fig. 12).
Apta para uso interior y exterior.
Categoría de aislamiento 3.
El voltaje y la frecuencia de funcionamiento seencuentran marcados en la placa de características. Asegúrese de que el motor sea apto
para la fuente de alimentación eléctrica a laque va a conectarse.
La bomba debe conectarse a la red eléctrica
por medio de un cable apantallado con conductor protector de masa. Es posible sustituirel cable de alimentación. Consulte la fig. 10.

30

Nota

La bomba MQ se puede alimentar
utilizando un generador o un
inversor. No obstante, la bomba
sólo funcionará satisfactoriamente si el generador o inversor
genera una onda perfectamente
sinusoidal con la entrada necesaria de potencia y voltaje. El generador debe dimensionarse superando en un 10 % el valor P1(entrada de potencia) de la bomba.
Si desea conocer el valor de P1,
consulte la sección
12.1 Dimensiones.

Grundfos.book Page 31 Monday, May 23, 2011 10:17 AM

Español (MX)

8.2 Diagrama de cableado

C

Rojo (vivo)
Negro

Amarillo
BlancoAmarillo

Motor eléctrico

Amarillo

Condensador

8.2.1 115 V

Amarillo / verde (masa)
Negro (fase)> CableBlanco (neutro)
Naranja
Negro
Rojo> Sensor de flujo> Presostato

TM02 2424 4708

B A

Fig. 12 Diagrama de cableado - 115 V

8.3 Medida de la resistencia de bobinado
Motor[V/Hz]

Punto de medida

Bobinado

Resistencia[ ± 10 %]115/60A-B (negro - rojo)
A-C (negro - blanco)

Principal
Auxiliar

1,4
5,5

Temperatura ambiente
[°F]

[°C]

70

21

La medida puede realizarse con o sin los cables conectados a la placa PCB y el condensador.

31

Grundfos.book Page 32 Monday, May 23, 2011 10:17 AM

Condensador

Rojo (vivo)
Azul

Amarillo
BlancoAmarillo

Motor eléctrico

Amarillo

Amarillo / verde (masa)
Negro (fase)> CableBlanco (neutro)
Naranja
Negro
Rojo> Sensor de flujo> Presostato

B A
TM02 2424 2409

Español (MX)8.3.1 230 V

Fig. 13 Diagrama de cableado - 230 V

8.4 Medida de la resistencia de bobinado
Motor[V/Hz]

Punto de medida

230/60A-B (azul - rojo)
A-C (azul - blanco)

Bobinado
Principal
Auxiliar

Resistencia[ ± 10 %]5,4
5,4Temperatura ambiente
[°F]

[°C]

70

21

La medida puede realizarse con o sin los cables conectados a la placa PCB y el condensador.

32

Grundfos.book Page 33 Monday, May 23, 2011 10:17 AM

Español (MX)8.5 Puesta en marcha

TM01 9696 2600

Antes de su puesta en marcha, la bomba debe
llenarse con entre 1,2 y 1,5 galones de aguapara permitir que se cebe. Consulte la fig. 14.
La bomba cuenta con una función de autocebado con una altura de succión máxima de
25 ft.

Fig. 14 Cebar la bomba
Una vez puesta en marcha, la bomba comenzará a autocebarse. Tras la fase de cebado, labomba pasará automáticamente al modo defuncionamiento normal. Si la fase de cebado
no finaliza antes de 5 minutos, la bomba se
detendrá automáticamente e intentará volver a
ponerse en marcha después de 30 minutes.
Es posible restablecer la bomba manualmente. Para ello, siga los pasos descritos en
el punto 2 de la tabla de la sección 9.1 Panelde control.

33

Grundfos.book Page 34 Monday, May 23, 2011 10:17 AM

9.1 Panel de control
La bomba MQ se controla íntegramente a través del panel de control. Consulte la fig. 1.
El panel de control ofrece la posibilidad deponer en marcha / detener la bomba. La configuración de la bomba y sus condiciones demantenimiento pueden conocerse por mediode los indicadores luminosos. Consulte la
fig. 15.

TM01 9684 2600

Español (MX)9. Funciones

Fig. 15 Panel de control
Las funciones del panel de control se describen en la tabla siguiente:
Ilustración

Descripción

1

Indicador luminoso (rojo)
Si el indicador luminoso se encuentra encendido,
indica que la bomba está en estado de reposo.

2

Botón de encendido / apagado
La bomba se pone en marcha / detiene por medio delbotón de encendido / apagado.
El botón de encendido / apagado también se puede
usar para restablecer manualmente la bomba en casode que se genere una situación de alarma:•

3

púlselo una vez para restablecer la bomba,
y púlselo de nuevo para ponerla en marcha.
Indicador luminoso (verde)
Indica que la bomba se encuentra preparada para funcionar.
Si el indicador luminoso se encuentra encendido,
indica que la bomba se pondrá automáticamente en
marcha si se consume agua. La bomba se detendrá
unos segundos después de que cese el consumo de
agua.

34

4

Español (MX)Grundfos.book Page 35 Monday, May 23, 2011 10:17 AM

Bomba encendida (verde)
El indicador luminoso se activa cuando la bomba seencuentra en funcionamiento.

5

Restablecimiento automático (verde)
De forma predeterminada, esta función se encuentra
activada.
•

Si el indicador luminoso se encuentra encendido,
indica que la función de restablecimiento automático está activada. La bomba intentará volver a
ponerse en marcha automáticamente cada
30 minutos después de una alarma / avería
durante un periodo de 24 horas. Una vez
transcurrido dicho periodo, la bomba permanecerá
en estado de alarma.

•

Si el indicador luminoso se encuentra apagado,
indica que la función de restablecimiento automático está desactivada. La bomba no volverá aponerse en marcha después de una alarma /avería.

La función de restablecimiento automático puede activarse / desactivarse manteniendo el botón de encendido / apagado durante 5 segundos.

6

Nota: Durante el consumo de agua, la bomba se poneen marcha y se detiene automáticamente, independientemente de si el indicador luminoso de restablecimiento automático se encuentra encendido o apagado.
Alarma (rojo)
El indicador luminoso se enciende si la bomba seencuentra en estado de alarma.
El estado de alarma podría haber sido provocado por:•

funcionamiento en seco•exceso de temperatura•

motor sobrecargado•

motor / bomba agarrotados.

Consulte la sección 9.2 Paro de la bomba.

35

Grundfos.book Page 36 Monday, May 23, 2011 10:17 AM

Español (MX)9.2 Paro de la bomba
La bomba está equipada con una función deprotección que provoca que la bomba se
detenga en caso de•funcionamiento en seco•exceso de temperatura•

motor sobrecargado•

motor / bomba agarrotados.

La bomba volverá a ponerse en marcha automáticamente después de 30 minutos (durante
24 horas) si se produce cualquier tipo de avería y la función de restablecimiento automático
está activada (el indicador luminoso de color
verde del panel de control debe encontrarse
activado, consulte el punto 5 de la tabla de lasección 9.1 Panel de control).

Nota

36

La configuración de la bomba se
almacena. Tras una falla en elsuministro eléctrico, la bomba
recupera automáticamente su
anterior estado de funcionamiento al restaurarlo.

10. Mantenimiento
En condiciones de funcionamiento normales,la bomba no precisa mantenimiento. No obstante, se recomienda mantener la bomba limpia.

ADVERTENCIA
No retire el depósito a presión dela bomba a menos que se hayaventilado a través de la válvula deescape de aire.

10.2 Puesta en marcha tras un periodo
prolongado de inactividad
La cubierta posterior incorpora un tapón que
se puede retirar utilizando la herramienta adecuada. Consulte la fig. 17. Ello permite liberar
el rotor de la bomba si se encuentra agarrotado como resultado de un periodo de inactividad. Si ha sido drenada, la bomba deberá llenarse de líquido antes de ponerla en marcha.
Consulte la fig. 14.

No toque los componentes electrónicos a menos que la bomba sehaya mantenido desconectada
durante, al menos, 5 minutos.

TM04 3633 4608

Si existe riesgo de daños por congelación,
drene la bomba a través del orificio de drenaje
y afloje la tuerca de unión del tubo de descarga. Consulte la fig. 16. La bomba debe llenarse de líquido antes de arrancarla de nuevo.
Consulte la fig. 14.

TM01 9697 4403

Fig. 17 Retirar el tapón de la cubierta
posteriorFig. 16 Drenaje de la bomba

10.1 Kits de mantenimiento
Existen kits de mantenimiento disponibles
para la bomba MQ. Los kits de servicio se
componen de los siguientes componentes
sustituibles:•

sello de flecha

•

motor

•

unidades electrónicas•

componentes hidráulicos.

11. Mantenimiento
Nota

Si una bomba se utiliza para bombear líquidos perjudiciales para lasalud o tóxicos, se clasificará
como contaminada.

Si se solicita a Grundfos la inspección de labomba, deberán enviarse los detalles relacionados con el líquido bombeado, etc. antes deenviar la bomba para su inspección. De lo
contrario, Grundfos podría rechazar la inspección de la bomba.
Los posibles gastos de devolución de labomba correrán por cuenta del cliente.
No obstante, todas las solicitudes de reparación (independientemente de a quién vayan
dirigidas) deberán incluir los detalles acercadel líquido bombeado si la bomba se ha utilizado con líquidos perjudiciales para la salud otóxicos.

37

Español (MX)Grundfos.book Page 37 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 38 Monday, May 23, 2011 10:17 AM

12.1 Dimensiones

TM01 9799 508

Español (MX)

12. Datos técnicos

12.2 Datos eléctricos
MQ 3-35

MQ 3-45

Tipo de protección

3

Categoría de protección

IP 54

Categoría de aislamiento

B

Cable de suministro eléctrico
Voltaje, consumo depotencia, P1 [W]

6.56 ft SJTW 18 awg con/sin enchufe

1 x 115-120 V – 10/+ 6 %, 60 Hz

900 W / 8,0 A

1100 W / 10,0 A

1 x 220-240 V – 10/+ 6 %, 60 Hz

850 / 4,0 A

1050 / 4,8 A

12.3 Homologaciones
Homologaciones UL y CSA.

13. Accesorios
ModeloDesignación

Número deproducto

MQ 3-35 / MQ 3-45

Cubierta protectora

96590745

38

14. Tabla de búsqueda de averías
AveríaCausa

Solución

1. No se puede
poner en marcha la bomba.

a) No hay agua suficiente.

Compruebe el suministro de agua /tubo de succión.

b) Se ha producido un sobrecalen- Suministre líquido frío a la bomba.
tamiento debido a que la temperatura del líquido es excesiva(superior a +95 °F / +35 °C).
c) Se ha producido un sobrecalen- Póngase en contacto con el proveetamiento debido a un agarrota- dor de la bomba.
miento / estrangulamiento de labomba.

2. La bomba no
se detiene.

d) El voltaje de suministro es
demasiado alto o demasiado
bajo.

Compruebe el voltaje de suministro
y corrija la avería, si es posible.

e) La bomba no recibe suministro
eléctrico.

Conecte el suministro eléctrico.

f)Abra un grifo. Compruebe que laseparación entre el punto superiordel tubo de descarga y la bomba no
sea superior a 50 ft.

No se consume agua.

g) El eje está bloqueado.

Gire el eje según lo descrito en lasección 10.2h) La bomba se encuentra en
estado de alarma.

Restablezca la bomba utilizando elbotón de encendido / apagado.
Consulte el punto 2 de la tabla de lasección 9.1 Panel de control.

a) Existe una fuga en el sistemade tuberías o éste no está bien
instalado.

Repare el sistema de tuberías.

b) La válvula de retención está
bloqueada o no se encuentra
instalada.

Limpie la válvula o instale una válvula de retención nueva.

3. La bomba sea) La bomba está funcionando en Compruebe el suministro de agua /detiene duranteseco.
tubo de succión.
el funcionab) Se ha producido un sobrecalen- Suministre líquido frío a la bomba.
miento.
tamiento debido a que la temperatura del líquido es excesiva(superior a +95 °F / +35 °C).
c) Se ha producido un sobrecalen- Póngase en contacto con el proveetamiento provocado por:dor de la bomba.
– una alta temperatura ambiental (> 113 °F/45 °C)– una sobrecarga del motor– un agarrotamiento del motor /bomba.
d) El voltaje de suministro es
demasiado bajo.

Compruebe el voltaje de suministro
y corrija la avería, si es posible.

39

Español (MX)Grundfos.book Page 39 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 40 Monday, May 23, 2011 10:17 AM

Español (MX)AveríaCausa

Solución

4. La bomba se
pone en marcha y se
detiene condemasiada frecuencia.

a) Existe una fuga en el tubo desucción o aire en el agua.

Compruebe el agua y el tubo desuministro / succión.

5. La bomba
transmite descargas eléctricas.

a) La conexión a tierra se ha reali- Conecte la conexión a tierra de lazado de forma incorrecta.
bomba de acuerdo con los reglamentos locales.

6. La bomba se
pone en marcha aunque nose consuma
agua.

a) La válvula de retención interna
está defectuosa o el sistema detuberías presenta fugas o está
defectuoso.

b) La presión del depósito a preCompruebe la presión del depósito
sión es demasiado alta o dema- a presión. Consulte la sección
siado baja.
6. Condiciones de funcionamiento.

Limpie la válvula o instale una
nueva.

Si la bomba no se pone en marcha una vez corregida la avería, póngase en contacto con el proveedor de la bomba o con Grundfos para obtener más información.

40

15. Preguntas frecuentes acerca de la bomba MQ
1. ¿Qué provoca que la bomba MQ se
ponga en marcha?
Respuesta: La bomba MQ está equipada
con un interruptor de caudal interno y unpresostato. Ambos pueden poner en marcha la bomba MQ dependiendo del consumo de agua. La bomba se pondrá enmarcha si:
El caudal es superior a 0,3 gpm
O
la presión es inferior a 29 psi.
2. ¿Qué provoca que la bomba MQ sedetenga?
Respuesta: Además del uso del botón deencendido / apagado manual, únicamente
el interruptor de caudal está autorizado adetener automáticamente la bomba MQ
durante su funcionamiento normal si elcaudal cae por debajo de 0,3 gpm. La
bomba se detiene entre 12 y 15 segundos
después de que el caudal se detenga.
Por otra parte, la bomba MQ se detiene
también en caso de funcionamiento en
seco o si se activa una alarma de excesode temperatura.

4. ¿Cual es la finalidad del depósito apresión integrado?
Respuesta: El depósito a presión integrado viene presurizado de fábrica a,aproximadamente, 23 psi (con la presiónde la bomba a cero) y contiene un volumen
de 14 onzas de agua. Ha sido diseñado
para minimizar la puesta en marcha delmotor provocada por pequeñas fugas.
5. ¿Cómo se determina el estado defuncionamiento en seco?
Respuesta: La alarma de funcionamiento
en seco se activa cuando el motor seencuentra en funcionamiento, el caudal es
inferior a 1,6 gpm Y la presión es inferior aaquella configurada en el presostato.
Si dicha condición perdura durante
12 segundos, la alarma se activa una vez
transcurrido 1 minuto y el motor se detiene.
La bomba MQ intentará volver a ponerse
en marcha automáticamente cada 30 minutos durante un periodo de 24 horas.
Si transcurren más de 24 horas sin que
penetre agua en la bomba, la bomba
deberá volver a ponerse en marcha
manualmente.

3. ¿Cuál es la altura máxima de un grifo
situado por encima de la bomba MQ?
Respuesta: Si se instala un grifo o espita a
una altura superior a 50 ft por encima de labomba MQ, existirá el posible riesgo deque la bomba MQ no se ponga nunca en
marcha. Si la bomba MQ se pone en marcha debido a un nivel bajo de presión (caudales reducidos), la presión deberá caer
por debajo del punto de activación del presostato (entre 28 y 30 psi de forma predeterminada). A fin de poder utilizar la bomba
con una presión de agua de 50 ft manteniendo las tolerancias y un cierto margende seguridad, se recomienda aplicar unlímite máximo de altura de 50 ft entre labomba MQ y cualquier grifo.

41

Español (MX)Grundfos.book Page 41 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 42 Monday, May 23, 2011 10:17 AM

Español (MX)6. ¿Cuál es la presión máxima de entrada
admisible en la bomba MQ?
Respuesta: Tanto en el caso de la bomba
MQ 3-35 como en el de la bomba MQ 3-45,
la presión interna máxima admisible es de109 psi. La presión máxima de entrada
sumada a la presión de la bomba MQ nodebe superar los 109 psi.
Recuerde que la presión de entrada debe
sumarse a la presión de la bomba MQ, porlo que si se aplica una presión de entrada
de 40 psi a la bomba MQ 3-45, podrían
alcanzarse presiones internas de aproximadamente 105 psi (65 + 40 psi).
Por otra parte, si las presiones de entrada
superan la presión del punto de activacióndel presostato integrado (entre 28 y 30 psi
de forma predeterminada), el presostato no
se podrá activar y se perderá la capacidad
de poner en marcha la bomba MQ con
niveles reducidos de caudal. En tal situación, sólo el interruptor de caudal podrá
poner en marcha la bomba MQ con niveles
reducidos de caudal por encima de su
punto de activación, de 0,3 gpm.

9. ¿Dónde es más sencillo instalar un
manómetro para medir la presión dedescarga?
Respuesta: En la tubería de descarga o enel orificio de rosca recta GAS de 3/8" quese utiliza para agregar agua de cebado a labomba.

16. Eliminación
La eliminación de este producto o las piezas
que lo componen debe realizarse de forma
respetuosa con el medio ambiente:
1. Solicite ayuda a un servicio de recogida deresiduos público o privado.
2. Si esto no fuera posible, póngase en contacto con la delegación u oficina de asistencia de Grundfos más cercana.

7. ¿Cuál es la capacidad de cebado de labomba MQ?
Respuesta: Aprox. 1,2 galones.
8. ¿Cómo se detecta la temperatura desobre carga / exceso de temperatura en
la bomba MQ?
Respuesta: El motor cuenta con un interruptor térmico incorporado en el bobinado.
El interruptor detiene el motor y lo pone en
marcha de nuevo. Consulte la tabla
siguiente.
Protección térmica
[V]

[°F]

[°C]

Desactivación

115

302

150

230

275

135

Activación

Ambos

151

65-67

Sujeto a modificaciones.
42

Français (CA) Notice d'installation et de fonctionnement
1. Introduction

SOMMAIRE
Page
1.

Introduction

2.

Composants fournis

3.

Symboles utilisés dans ce document

4.
4.1

Applications
Liquides pompés

5.
5.1

Identification
Désignation

6.
6.1

Conditions de fonctionnement
Hauteur d'aspiration

7.
7.1
7.2
7.3
7.4
7.5

Installation mécanique
Lieu d'installation
Base
Dégagement requis
Tuyauterie
Couvercle de protection

8.
8.1
8.2
8.3
8.4
8.5

Branchement électriqueGénérateur ou inverseur
Schéma de câblage
Mesure résistance d'enroulement
Mesure de la résistance d'enroulement
Démarrage

9.
9.1
9.2

Fonctions
Panneau de commandeArrêt de la pompe

10.
10.1
10.2

Maintenance
Kits de service
Démarrage après une longue périoded'inactivité

11.

Service

12.
12.1
12.2
12.3

Caractéristiques techniques
Dimensions
Caractéristiques électriques
Approbations

13.

Accessoires

14.

Tableau de recherche de défauts

15.

Questions fréquemment posées
concernant la pompe MQ

16.

Mise au rebut

43
43
44
44
44
45
45
46
46
47
47
47
47
47
49
50
50
51
51
52
53
54
54
55
56
56
56
56
57
57
57
57
57
58

Le groupe MQ est un système d'alimentationd'eau à faible sonorité composé d'une pompe,
d'un moteur, d'un réservoir sous pression etd'un système de commande combinés dansune unité compacte. La pompe est conçue
pour une utilisation en intérieur et en extérieur.
La pompe auto-amorçante démarre automatiquement quand l'eau est consommée dansl'installation et s'arrête dès que la consommation cesse. Le clapet anti-retour interne intégréempêche le refoulement pendant l'auto-amorçage et le fonctionnement.
La pompe MQ est équipée d'une protection
contre la surchauffe et la marche à sec ainsi
que d'un panneau de commande facile à utiliser.
Le réservoir sous pression intégré réduit lenombre de démarrages et d'arrêts, en cas defuites dans l'installation.

2. Composants fournis
Le colis du MQ contient :•un système d'alimentation d'eau MQ avec
clapet anti-retour intégré•

un clapet d'entrée anti-retour en sachet
plastique•une notice d'installation et de fonctionnement.

60
61

AVERTISSEMENT
Avant de procéder à l'installation,
veuillez lire cette notice d'installation et de fonctionnement. L'installation et le fonctionnement
doivent être conformes à la réglementation locale et aux règles debonne pratique en vigueur.
43

Français (CA)Grundfos.book Page 43 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 44 Monday, May 23, 2011 10:17 AM

Français (CA)

3. Symboles utilisés dans ce
document

AVERTISSEMENT
Le non respect de ces consignesde sécurité peut entraîner desaccidents corporels.

Précaution

Le non respect de ces consignesde sécurité peut entraîner des dysfonctionnements ou des dommages à l'équipement.

Nota

Remarques ou instructions facilitant le travail et assurant un fonctionnement sécurisé.

4. Applications
Le groupe d'alimentation d'eau MQ est conçu
pour les applications types suivantes :•surpression d’eau(pression d'entrée maximale : 40 psi).

•alimentation en eau en provenance depuits(hauteur d'aspiration maximale : 7,62 m,
25 pieds), par exemple– dans les résidences privées– dans les exploitations agricoles– dans les jardins maraîchers et autres
grands espaces verts.

La pompe est adaptée à l'eau de pluie.

4.1 Liquides pompés
Liquides fluides, clairs, non agressifs necontenant pas de particules solides ni defibres.

44

Grundfos.book Page 45 Monday, May 23, 2011 10:17 AM

Français (CA)

5. Identification
5.1 Désignation
ExempleMQ

3 -35 A -O -A BVBPType de pompe
Débit nominal [m³/h]
Hauteur [m]Code du modèle de pompe
A: Norme
Code du raccordement tuyauterie
Code des matériaux
A: Norme
Code joint d'arbre

Couvercle de protection(accessoire)
Couvercle
réservoir
sous pression

Panneau de commandeOrifice de refoulement
Bouchon d'amorçage

Orificed'aspiration

Bouchon devidangeFig. 1

Socle

TM04 3648 4908

Bouchon ducouvercle
d'extrémité

Système d'alimentation d'eau MQ. Le couvercle de protection est requis pour une utilisation en extérieur

45

Grundfos.book Page 46 Monday, May 23, 2011 10:17 AM

Français (CA)6. Conditions de fonctionnement
MQ 3-35
Débit maximal [gpm]Pression maximale [psi]MQ 3-45
22

51

65

Pression de service maximale [psi]108

Hauteur maximale d'aspiration [pieds],
voir page 49

25

Température ambiante minimale [°F]/[°C]32/0Température ambiante maximale [°F]/[°C]

113/45Température minimale du liquide [°F]/[°C]32/0Température maximale du liquide [°F]/[°C]95/35

Poids net [lbs]29

Niveau de pression sonore [dB(A)]< 70

Capacité du réservoir [oz]13,5Pression d'air dans le réservoir [psi]22 à 25

Branchements

1" NPT

Bouchons de vidange et d'amorçage

3/8" GAS

6.1 Hauteur d'aspiration
La hauteur maximale d'aspiration de la pompe
peut être déterminée d'après le schéma de lapage 49.
ExempleSi la hauteur d'aspiration est de 3 m(10 pieds), la longueur du conduit d'aspiration
ne doit pas dépasser 22 m (72 pieds).

46

7. Installation mécanique

7.3 Dégagement requis

7.1 Lieu d'installation
La pompe est conçue pour une installation en
intérieur et en extérieur. Elle résiste à lalumière du soleil.

Nota

Si la pompe est installée en extérieur, elle doit être équipée d'uncouvercle de protection (accessoire). Voir paragr. 7.5 Couvercle
de protection et 13. Accessoires.

Nota

En cas de fuite interne accidentelle, le liquide pompé sera
vidangé du socle et/ou du couvercle d'extrémité pour éviter
d'endommager la pompe. Installer
la pompe de manière à éviter tout
dommage collatéral indésirable.

Installer la pompe sur le socle, avec l'orificed’aspiration à l'horizontale et l'orifice de refoulement à la verticale.
La pompe doit être installée horizontalement.
Angle d'inclinaison maximal admissible :± 18 °. Voir fig. 2.

Fig. 3

La pompe étant auto-refroidie, elle ne nécessite ni dégagement ni ventilation sur les côtés.

Nota

TM01 9691 2600

S'assurer que les températuresambiantes maximales nedépassent pas les valeurs indiquées au paragr. 6. Conditions defonctionnement.

7.4 Tuyauterie
Nota

Ne jamais forcer lors du raccordement de conduits.

La pompe est fournie avec des raccords filetésNPT 1". Fixer les raccords dans les orifices
d'aspiration et de refoulement. Voir fig. 4.
Pour faciliter la fixation, l'orifice de refoulement de la pompe est orientable, ± 5 °.

Installation horizontale de la pompe
MQ

Pour éviter mouvements et vibrations, lapompe et le socle peuvent être sécurisés à
une base solide, par les orifices de boulons
dans le socle. Pour raccordement tuyauterie,voir paragr. 7.4 Tuyauterie.

Dégagement minimal derrière lapompe

TM01 9698 2600

Fig. 2

TM04 3746 5008

60"

7.2 BaseMax. ± 18 °Pour l'inspection et l'entretien, prévoir undégagement d'au moins 150 cm (60") derrière
la pompe.

Fig. 4

Fixation des raccords filetés dansles orifices d'aspiration et de refoulement

47

Français (CA)Grundfos.book Page 47 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 48 Monday, May 23, 2011 10:17 AM

7.4.2 Flexible d'aspiration au lieu deconduit
Si un flexible d'aspiration est utilisé au lieu
d'un conduit, il ne doit pas excéder les longueurs indiquées dans le graphique, page 49.
Le flexible d'aspiration doit être d'au moins
Ø1". Le flexible doit être de type semi-rigide.

TM04 4271 1009

7.4.3 Conduits d'aspiration longs

Fig. 5

Correct : serrer manuellementl'écrou-union de refoulement

Fig. 6

Incorrect : ne pas utiliser d'outil
pour serrer l'écrou-union de refoulement

TM 044272 1009

7.4.1 Conduits d'aspiration branchés à unpuits
Si la pompe est utilisée pour le pompage d'un
puits, il est recommandé d'installer un clapetde pied à l'extrémité du conduit d'aspiration.
Voir fig. 7.

Clapet depiedFig. 748

Conduits d'aspiration branchés à
un puits

Un clapet d'entrée anti-retour séparé est fourni
avec la pompe. Avec les conduits d'aspiration
longs, il est recommandé de fixer un clapet
d'entrée anti-retour dans l'orifice d'aspirationde la pompe. Voir paragr. 7.4.4 Installation duclapet anti-retour en entrée
Les conduits doivent être soutenus de manière
adéquate, de chaque côté de la pompe, pouréviter des contraintes sur les raccords de lapompe.

TM01 9693 2600

Français (CA)

Visser avec précaution le raccord de refoulement dans l'orifice de refoulement avec une
clé ou un outil similaire. Maintenir le raccord
de refoulement et serrer manuellementl'écrou-union de refoulement de la pompe.
Voir fig. 5.

7.5 Couvercle de protection

7.4.4 Installation du clapet anti-retour enentréeLe clapet d'entrée anti-retour réduit le risqued'infiltration d'amorçage de la pompe, dans lesapplications d'aspiration négative. Il augmenteaussi la capacité d'auto-aspiration, parexemple avec de l'eau provenant d'une
citerne.
Installer le clapet d'entrée anti-retour de lamanière suivante, voir fig. 8.
1. Retirer le branchement d'aspiration de lapompe.
2. Fixer le clapet d'entrée anti-retour dansl'orifice d'aspiration, dans la direction indiquée en fig. 8.
3. Rebrancher le raccord de pompe.

Le couvercle de protection protège le panneaude commande des intempéries. Il est disponible en option. Voir paragr. 13. Accessoires.
Pour fixer le couvercle de protection, le cliquer
sur le haut du panneau de commande pourqu'il s'emboîte dans les nervures supérieuresde refroidissement.
Pour retirer le couvercle, tirer les deux clips
vers l'extérieur, le libérer des nervures derefroidissement et le tirer vers le haut.

Les applications avec pression
d'entrée positive ne nécessitent
pas l'installation d'un clapet
d'entrée anti-retour. La pompe MQ
est en effet équipée d'un clapet
anti-retour interne côté refoulement.

TM04 3745 5008

Nota

Nota

L'absence d'utilisation du couvercle de protection sur les installations en extérieur rend la garantie caduque.

Couvercle de protection

TM 04 4121 0809

Fig. 9Fig. 8Installation du clapet d'entrée antiretour

49

Français (CA)Grundfos.book Page 49 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 50 Monday, May 23, 2011 10:17 AM

TM01 9694 2600

Les branchements électriques et protections
complémentaires doivent être effectués par unélectricien agréé, conformément aux réglementations locales.

AVERTISSEMENT
Pompe non submersible.
Si le câble d'alimentation est
endommagé, il doit être remplacépar le fabricant, un réparateur
agréé Grundfos ou des personnes
qualifiées et autorisées pour éviter
des risques.
Ne jamais effectuer de branchements dans la boîte à bornes de lapompe, sauf si l’alimentation électrique a été mise hors tension pendant au moins 5 min.

Fig. 10 Branchement électrique
Brancher le câble d'alimentation de la pompe
au réseau électrique. Une fois le câble branché, un voyant vert et un voyant rouge situés
sur la panneau de commande s'allument.
Voir fig. 11.

Risque de choc électrique.
Cette pompe est fournie avec un fil
de mise à terre et une fiche demise à terre. Pour réduire le risquede choc électrique, brancher uniquement sur un circuit protégé par
un disjoncteur différentiel de type
GFCI.
Cette pompe n'est ni conçue ni
testée pour une utilisation en piscines ou dans les zones marines.
Cette pompe a été évaluée uniquement pour une utilisation avec del’eau.

TM01 9695 2600

Français (CA)

8. Branchement électriqueFig. 11 Branchement du câble d'alimentation secteur

8.1 Générateur ou inverseur

Ne pas démarrer la pompe avant
de l'avoir remplie d'eau (amorcée,voir fig. 12).
Convient pour une utilisation en
intérieur et en extérieur.
Type de protection 3.
La fréquence et la tension de fonctionnement
sont indiquées sur la plaque signalétique.
S’assurer que le moteur est conçu pour l’alimentation électrique qui sera utilisée.
La pompe doit être branchée au réseau d'alimentation par un câble gainé avec protection
à la terre. Il est possible de remplacer le câbled'alimentation électrique. Voir fig. 10.

50

Nota

Le groupe MQ peut être alimenté
par un générateur ou par un inverseur. Cependant, la pompe nefonctionnera de manière satisfaisante que si le générateur ou
l'inverseur fournissent une véritable onde sinusoidale avec lapuissance et la tension d'entrée
nécessaires. Le générateur doitêtre dimensionné 10 % au-dessus
du P1 (puissance d'entrée) de lapompe. Pour P1, voir paragr.
12.1 Dimensions.

Grundfos.book Page 51 Monday, May 23, 2011 10:17 AM

Français (CA)8.2 Schéma de câblage

CRouge (principal)
Noir

Jaune
Blanc

Jaune

Moteur électrique

Jaune

Condensateur

8.2.1 115 V

Jaune/vert (terre)
Noir (phase)
Blanc (neutre)
OrangeNoir
Rouge> Câble> Capteur débit> Pressostat

TM02 2424 4708

B A

Fig. 12 Schéma de câblage - 115 V

8.3 Mesure résistance d'enroulement
Moteur[V/Hz]
115/60

Point de mesure Enroulement

Résistance[ ± 10 %]A-B (noir - rouge)

Principal

1,4

A-C (noir- blanc)

Aux.

5,5

Température ambiante
[°F]

[°C]

70

21

La mesure peut être effectuée avec ou sans câbles raccordés au PCB et au condensateur.

51

Grundfos.book Page 52 Monday, May 23, 2011 10:17 AM

Condensateur

Rouge (principal)
Bleu

Jaune
Blanc

Jaune

Moteur électrique

Jaune

Jaune/vert (terre)
Noir (phase)
Blanc (neutre)
OrangeNoir
Rouge> Câble> Capteur débit> Pressostat

B A
TM02 2424 2409

Français (CA)8.3.1 230 V

Fig. 13 Schéma de câblage - 230 V

8.4 Mesure de la résistance d'enroulement
Moteur[V/Hz]
230/60

Point de mesure

Enroulement

Résistance[ ± 10 %]A-B (bleu - rouge)

Principal

5,4

A-C (bleu - blanc)

Aux.

5,4

Température ambiante
[°F]

[°C]

70

21

La mesure peut être effectuée avec ou sans câbles raccordés au PCB et au condensateur.

52

Grundfos.book Page 53 Monday, May 23, 2011 10:17 AM

Français (CA)

8.5 Démarrage

TM01 9696 2600

Avant le démarrage, la pompe doit être remplie avec 4,5 l à 5,7 l (1,2 à 1,5 gallons) d'eau
pour permettre l'auto-amorçage, voir fig. 14.
La pompe est auto-amorçante avec hauteurd'aspiration maximale de 7,6 m (25 pieds).

Fig. 14 Amorçage de la pompe
Une fois démarrée, la pompe commence à
s'auto-amorcer. Une fois amorcée, elle passe
automatiquement en fonctionnement normal.
Si l'amorçage ne s'est pas terminé au bout de
5 min, la pompe s'arrête automatiquement.
Elle essaie de redémarrer 30 min plus tard.
Il est possible de réinitialiser la pompe
manuellement. Voir point 2 du tableau au
paragr. 9.1 Panneau de commande.

53

Grundfos.book Page 54 Monday, May 23, 2011 10:17 AM

9.1 Panneau de commande
La pompe MQ est entièrement commandéepar le panneau de commande. Voir fig. 1.
Le panneau de commande permet le démarrage et l'arrêt de la pompe. Les réglages de lapompe et les conditions de fonctionnement
sont indiqués par des voyants lumineux.
Voir fig. 15.

TM01 9684 2600

Français (CA)

9. Fonctions

Fig. 15 Panneau de commande
Les fonctions du panneau de commande sont décrites sur le tableau ci-dessous.
Illustration

Description

1

Voyant rouge
Si ce voyant est allumé, la pompe est en atttente.

2

Bouton On/Off (marche/arrêt)La pompe est démarrée/arrêtée avec le bouton On/Off(marche /arrêt).
On/Off (marche/arrêt) peut aussi être utilisé pour une
réinitialisation manuelle, en cas d'alarme :•3

appuyer une fois pour réinitialiser• appuyer une nouvelle fois pour démarrer.
Voyant vert
Indique que la pompe est prête à fonctionner.
Si ce voyant est allumé, la pompe démarre automatiquement, une fois l'eau consommée. La pompes'arrête quelques secondes après la fin de la consommation.

54

4Français (CA)Grundfos.book Page 55 Monday, May 23, 2011 10:17 AM

Pump on (pompe en marche) (vert)
Ce voyant est allumé quand la pompe fonctionne.

5

Auto reset (réinitialisation automatique) (vert)
En standard, la fonction est activée à la livraison.
•

Si ce voyant est allumé, la fonction de réinitialisation automatique (Auto reset) est activée.
La pompe essaie automatiquement de redémarrer
toutes les 30 min après un défaut ou une alarme,
ceci pendant 24 h. Une fois passé ce délai,la pompe reste dans la condition d'alarme.

•

Une fois le voyant éteint, la fonction de réinitialisation automatique (Auto reset) est désactivée.
La pompe ne redémarre pas après un défaut ou
une alarme.

La fonction de réinitialisation automatique (Auto reset)
peut être activée/désactivée en appuyant sur le bouton On/Off pendant 5 secondes.
Remarque - Une fois l'eau consommée, la pompe
démarre et s'arrête automatiquement, si le voyant
Auto-reset (réinitialisation automatique) est allumé.
Alarme (rouge)

6

Le voyant s'allume quand la pompe est en conditiond'alarme.
La condition d'alarme peut être activée par :•marche à sec•

surchauffe•surcharge du moteur•

grippage du moteur ou de la pompe.

Voir paragr. 9.2 Arrêt de la pompe.

9.2 Arrêt de la pompe
Une fonction électronique de protection est
intégrée à la pompe. Elle arrête la pompe encas :•de marche à sec,•de surchauffe,•de surcharge du moteur•de grippage du moteur ou de la pompe.

Nota

Les réglages de la pompe sontenregistrés. Après une coupure decourant, la pompe revient automatiquement aux conditions de fonctionnement précédentes, une fois
l'alimentation électrique rétablie.

La pompe redémarre automatiquement après
30 min (pendant 24 h) en cas de défaut, si lafonction de réinitialisation automatique (Autoreset) est activée (voyant vert du panneau decommande allumé, voir point 5 sur le tableau
au paragr. 9.1 Panneau de commande).

55

Grundfos.book Page 56 Monday, May 23, 2011 10:17 AM

Dans des conditions de fonctionnement normales, la pompe ne nécessite aucune maintenance. Il est toutefois recommandé de lamaintenir propre.

AVERTISSEMENT
Ne pas retirer de la pompe leréservoir sous pression sauf s'il aété purgé par la vis de purge d'air.
Ne jamais toucher les composantsélectroniques, sauf si la pompe aété mise hors tension pendant au
moins 5 min.

10.2 Démarrage après une longue
période d'inactivité
Le couvercle d'extrémité comporte un bouchon pouvant être retiré à l'aide d'un outil
approprié.
Voir fig. 17. Il est ainsi possible de libérer lerotor de la pompe si celui-ci est grippé notamment après une période d'inactivité. Si lapompe a été vidangée, elle doit être de nouveau remplie de liquide avant sa mise en
marche. Voir fig. 14.

Fig. 16 Vidange de la pompe

10.1 Kits de service
Des kits de service sont disponibles pour lapompe MQ. Les kits de service comprennent
les pièces détachées suivantes :•joint d'arbre,•

moteur,•composants électroniques,•composants hydrauliques.

56

TM04 3633 4608

En cas de risque de gel, vidanger la pompe
par l'orifice de vidange et desserrer l'écrouunion du conduit de refoulement, voir fig. 16.
La pompe doit être remplie de liquide avant leredémarrage. Voir fig. 14.

TM01 9697 4403

Français (CA)10. MaintenanceFig. 17 Retirer le bouchon du couvercle
d'extrémité

11. Service
Nota

Si une pompe a été utilisée avec
un liquide nuisible à la santé ou
toxique, la pompe sera classée
comme contaminée.

Avant de renvoyer la pompe chez Grundfos
pour révision, veuillez contacter Grundfos
pour fournir des détails sur le liquide pompé,
etc. Grundfos peut, sinon, refuser d'accepter
la pompe pour révision.
Les coûts éventuels de renvoi de la pompesont à la charge du client.
Toute demande de révision (adressée à qui
que ce soit), doit inclure des détails concernant le liquide pompé si la pompe a été utilisée avec des liquides nuisibles à la santé ou
toxiques.

Grundfos.book Page 57 Monday, May 23, 2011 10:17 AM

Français (CA)12. Caractéristiques techniques

TM01 9799 508

12.1 Dimensions

12.2 Caractéristiques électriques
MQ 3-35

MQ 3-45

Type de protection

3

Indice de protection

IP 54

Classe d'isolation

B

Câble d’alimentation

2 m (6,56 pieds) SJTW 18 awg
avec/sans fiche

Tension, consommationde puissance, P1 [W]

1 x 115-120 V – 10/+ 6 %,60 Hz

900 W/8,0 A

1100 W/10,0 A

1 x 220-240 V – 10/+ 6 %,60 Hz

850/4,0 A

1050/4,8 A

12.3 Approbations
Listé UL et homologué CSA.

13. Accessoires
ModèleDésignation

MQ 3-35 / MQ 3-45

Couvercle de protection

Numéro du produit
9659074557

Grundfos.book Page 58 Monday, May 23, 2011 10:17 AM

Français (CA)

14. Tableau de recherche de défauts
DéfautCause

Solution

1. La pompe nedémarre pas.

a) Pas assez d'eau.

Vérifier l'alimentation en eau/leconduit d'aspiration.

b) Surchauffe due à une tempéra- Verser du liquide froid sur la pompe.
ture de liquide excessive (audessus de +95 °F/+35 °C).
c) Surchauffe due à un grippage/
blocage de la pompe.

Contacter votre fournisseur depompe.

d) Tension d'alimentation trop éle- Vérifier la tension d'alimentation etvée ou trop faible.
corriger le défaut, si possible.

2. La pompe nes'arrête pas.

3. La pompes'arrête pendant le fonctionnement.

e) Pas d'alimentation électrique.

Brancher l’alimentation électrique.

f)Ouvrir un robinet. Vérifier que lahauteur entre le point le plus haut duconduit de refoulement et la pompe
ne dépasse pas 15,24 m (50 pieds).

Pas de consommation d'eau.

g) L'arbre est bloqué.

Faire tourner l'arbre comme décrit
sous 10.2.

h) La pompe est en condition
alarme.

Réinitialiser la pompe avec On/Off(marche/arrêt). Voir point 2 dutableau au paragr. 9.1 Panneau decommande.

a) Le conduit existant fuit ou est
défectueux.

Réparer la tuyauterie.

b) Le clapet anti-retour est bloqué
ou manque.

Nettoyer le clapet ou installer unnouveau clapet anti-retour.

a) Marche à sec.

Vérifier l'alimentation en eau/leconduit d'aspiration.

b) Surchauffe due à une tempéra- Verser du liquide froid sur la pompe.
ture de liquide excessive (audessus de +95 °F/+35 °C).
c) Surchauffe causée par :– une température ambianteélevée (> 113 °F/45 °C)

Contacter votre fournisseur depompe.

– une surcharge du moteur– le grippage du moteur ou de lapompe.

4. La pompe
démarre ets'arrête trop
fréquemment.

58d) Tension d'alimentation trop
faible.

Vérifier la tension d'alimentation etcorriger le défaut, si possible.

a) Fuite dans le conduit d'aspiration ou présence d'air dansl'eau.

Vérifier l'eau et le conduit d'aspiration/d'alimentation.

b) Pression trop faible ou trop éle- Vérifier la pression dans le réservoir
vée dans le réservoir sous
sous pression. Voir paragr.
pression.
6. Conditions de fonctionnement.

Défaut

Cause

Solution

5. La pompe provoque deschocs électriques.

a) Branchement à la terre défectueux.

Brancher la mise à terre à la pompe,
conformément aux réglementations
locales.

6. La pompe
démarre quand
il n'y a plus deconsommationd'eau.

a) Clapet anti-retour interne
Nettoyer le clapet ou en installer undéfectueux, fuite sur la tuyaute- nouveau.
rie existante ou tyauterie défectueuse.

Si la pompe ne démarre pas une fois le défaut corrigé, contacter votre fournisseur ou Grundfos
pour informations supplémentaires.

59

Français (CA)Grundfos.book Page 59 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 60 Monday, May 23, 2011 10:17 AM

Français (CA)15. Questions fréquemment posées concernant la pompe MQ
1. Qu'est-ce qui provoque le démarrage dela pompe MQ ?
Réponse - La pompe MQ est équipée d'uncommutateur de débit interne et d'un pressostat. Ces deux éléments peuvent fairedémarrer la pompe MQ, selon la consommation d'eau. La pompe démarre :si le débit est supérieur à 0,3 gpm
OU
si la pression est inférieure à 29 psi.
2. Qu'est-ce qui provoque l'arrêt de lapompe MQ ?
Réponse - Mis à part la touche manuelle
On/Off (marche/arrêt), seul l'interrupteur dedébit est autorisé à arrêter automatiquement la pompe MQ en cours de fonctionnement normal si le débit tombe à moins de
0,3 gpm. La pompe s'arrête 12 à 15 sec
après l'arrêt du débit.
La pompe MQ s'arrête également en cas
de marche à sec ou d'alarme indiquant une
surchauffe.
3. Quelle est la hauteur maximale d'unrobinet au-dessus de la pompe MQ ?
Réponse - Si on installe un robinet ou un
robinet de puisage à une hauteur de plusde 15 m(50 pieds) au-dessus de la pompe MQ, ellerisque de ne plus pouvoir démarrer. Si lapompe démarre pour cause de faible pression (débits faibles), la pression doit chuter
sous le point d'activation du pressostat(réglage usine 28 à 30 psi). Pour permettre
une pression de 15 m
(50 pieds) d'eau, des tolérances et une
marge de sécurité, nous recommandons
une hauteur maximale de 15 m (50 pieds)
entre la pompe et un robinet.

60

4. À quoi sert le réservoir sous pression
intégré ?
Réponse - Le réservoir sous pression intégré est déjà pressurisé en usine à environ
23 psi (avec pression de pompe à zéro) etcontient 0,42 l(14 onces) d'eau. Il est conçu pour minimiser un démarrage du moteur dû à delégères fuites.
5. Comment est déterminée la marche à
sec ?
Réponse - L'alarme pour marche à sec est
activée quand le moteur fonctionne ET que
le débit est moins de 1.6 gpm ET que lapression est inférieure au réglage du pressostat. Si cette situation se prolonge pendant 12 sec, l'alarme est activée après 1
min et le moteur s'arrête. La pompe MQtente de redémarrer automatiquement
toutes les 30 min pendant 24 h max.
Après plus de 24 h sans eau, redémarrer lapompe manuellement.
6. Quelle est la pression d'alimentation
maximale autorisée dans la pompe MQ ?
Réponse - Pour les pompes MQ 3-35 et
MQ 3-45, la pression interne maximale
autorisée est de 109 psi. La pression d'alimentation maximale, ajoutée à la pression
de la pompe MQ, ne doit pas dépasser
109 psi.
Ne pas oublier que la pression d'alimentation s'ajoute à la pression de la pompe MQ.
Donc, avec une pression d'alimentation de
40 psi fournie à la pompe MQ3-45, lespressions internes peuvent atteindre environ 105 psi (65 + 40 psi).
De plus, si les pressions d'alimentation
dépassent le point d'activation du pressostat intégré (réglage usine 28 à 30 psi), lepressostat ne pourra pas activer. On ne
pourra alors plus faire démarrer la pompe
MQ à de faibles débits. Dans ce cas, seull'interrupteur de débit pourra faire démarrer
la pompe MQ à des débits supérieurs à son
point d'activation de 0,3 gpm.

Grundfos.book Page 61 Monday, May 23, 2011 10:17 AM

Français (CA)

7. Quelle est la capacité d'amorçage de lapompe MQ ?
Réponse - Environ 4,5 l (1,2 gallons).
8. Comment est détectée la température desurcharge/surchauffe de la pompe MQ ?
Réponse - Le moteur est équipé d'un thermorupteur intégré aux enroulements dumoteur. Ce commutateur coupe le moteur
et le fait redémarrer. Voir tableau ci-dessous.
Protection thermique[V]
Déclenché
Enclenché

[°F]

[°C]

115

302

150

230

275

135

Les
deux

151

65-67

9. Où peut-on installer facilement un
manomètre pour mesurer la pression derefoulement ?
Réponse - Dans la tuyauterie de refoulement ou dans l'ouverture filetée droite 3/8"
GAS utilisée pour ajouter de l'eau d'amorçage à la pompe.

16. Mise au rebut
Ce produit ou ses composants doivent êtremis au rebut dans le respect de l'environnement.
1. Utiliser le service de voirie public ou privé.
2. Si cela n'est pas possible, contacter lasociété Grundfos la plus proche ou un atelier d'entretien.

Sous réserve de modifications.
61Grundfos.book Page 62 Monday, May 23, 2011 10:17 AM

1

Suction lift/suction pipe[ft] 28
24

20

16

12

8

4

0
0

10

20

30

40

50

60

70

80

90

Length of horizontal suction pipeLongueur de la tuyauterie d’aspiration horizontale
Longitud de la tubería de aspiración horizontal

62

100

110

120

[ft]

TM02 8327 4903

Total vertical suction lift
Hauteur d’aspiration verticale totale
Altura de aspiración vertical total

Appendix

AppendixGrundfos.book Page 63 Monday, May 23, 2011 10:17 AM

Appendix

Exploded view
166
164
174a
175

43
176a

42
152b
152c

161
176b

181
166a

174b

45

41

65
62

187

63
61a
186
160 6061

165
185
185a

168
7

44

64

184

152
152a

149

11a

169

100

51

100a

173
173a

53

52

150

100b
103
102

40a

27

40

26

180
104

38
37a

107
37a

2
4
37
49

67

66
66a

13

14

6
37b

93a

93

11b
11
10

94
91

16
7

92

11a

TM02 8410 5103

100c
101

63

Grundfos.book Page 64 Monday, May 23, 2011 10:17 AM

AppendixPos.

Description (US)Descripción (MX)Description (CA)2

Motor stool with base plate

Soporte del motor con base

Lanterne moteur avec socle

7

Priming plug

Tapón de cebado

Bouchon d’amorçage

14

Self-priming part

Pieza de autocebado

Pièce d’auto-amorçage

16

Pump sleeve

Camisa de la bomba

Chemise de pompe

42

Pressure tank

Tanque de presión

Réservoir sous pression

43

Cover

Tapa

Couvercle

51

End cover

Tapa final

Extrémité de la carcasse
Joint torique

53

O-ringJunta tórica

65

Check valve

Válvula de retención

Clapet anti-retour

100a

Discharge connection

Conexión de descarga

Raccord de refoulement

101

Inlet connection

Conexión de aspiración

Raccord d’aspiration

161

Capacitor

Condensador

Condensateur

174aPressure switch

PresostatoContacteur manométrique

64

181

Circuit board

Carta de circuito impreso

Carte de circuit imprimé184

Flow switch cover

Tapa del interruptor de caudal

Couvercle de l’interrupteur de débit

185

Flow switch wheel

Rueda del interruptor de caudal

Roue de l’interrupteur de débitGrundfos.book Page 65 Monday, May 23, 2011 10:17 AM

65

Grundfos.book Page 66 Monday, May 23, 2011 10:17 AM

66

USA

CanadaMéxicoGRUNDFOS Pumps Corporation
17100 West 118th Terrace
Olathe, Kansas 66061
Phone: +1-913-227-3400
Telefax: +1-913-227-3500
USA
Grundfos CBS Inc.
902 Koomey Road
77423 Brookshire, Texas
Phone: (+1) 281 294 2700
Telefax: (+1) 800 945 4777

GRUNDFOS Canada Inc.
2941 Brighton Road
Oakville, Ontario
L6H 6C9
Phone: +1-905 829 9533
Telefax: +1-905 829 9512

Bombas GRUNDFOS de México S.A. de
C.V.
Boulevard TLC No. 15
Parque Industrial Stiva
Aeropuerto
Apodaca, N.L.C.P. 66600
Phone: +52-81-8144 4000
Telefax: +52-81-8144 4010

USA
Peerless Pump Company
2005 Dr. Martin Luther King Jr. Street
P.O. Box 7026
46207-7026 Indianapolis, Indiana
Phone: (+1) 317 925 9661
Telefax: (+1) 317 924 7388

MéxicoPeerless Pumps Mexico, S.A de C.V.
Avenida Milimex 115
Parque Industrial Milimex
Apodaca N.L. 66600
Phone: (+52) 81 8625 9900
Telefax: (+52) 81 8625 9915

Addresses revised 11.08.2010

USA
Yeomans Chicago
Corporation
3905 Enterprise Court
IL 60504 Aurora
Phone: (+1) 630 236 5500
Telefax: (+1) 630 236 5511

Addresses revised 11.08.2010

Grundfos companies

Grundfos.book Page 1 Monday, May 23, 2011 10:17 AM

Grundfos.book Page 68 Monday, May 23, 2011 10:17 AM

Being responsible is our foundation
Thinking ahead makes it possible
Innovation is the essence

P1720439

V7173255 0511
Repl. V7173255 1010
ECM: 1076228
The name Grundfos, the Grundfos logo, and the payoff Be–Think–Innovate are registrated trademarks
owned by Grundfos Management A/S or Grundfos A/S, Denmark. All rights reserved worldwide.

www.grundfos.com