Cable junction unit
MODEL

FA1-MM40P
FA1-MM20P

User’s Manual(Detailed Edition)

Time and Wire Saving Devices

SAFETY PRECAUTIONS(Read these precautions before using the FA Goods products.)

Before using the products, please read this manual and the relevant manuals carefully, and pay full
attention to safety to handle the products correctly.
The precautions given in this manual are concerned with the FA Goods products only.
For the safety precautions of the programmable controller system, refer to the user's manual for the
programmable controller used.
If the equipment is used in a manner not specified by the manufacturer, the protection provided by theequipment may be impaired.
In this manual, the safety precautions are classified into two levels: " WARNING" and " CAUTION".

WARNING

Indicates that incorrect handling may cause hazardous
conditions, resulting in death or severe injury.

CAUTION

Indicates that incorrect handling may cause hazardous
conditions, resulting in minor or moderate injury orproperty damage.

Under some circumstances, failure to observe the precautions given under " CAUTION" may leadto serious consequences.
Observe the precautions of both levels because they are important for personal and system safety.

2

[Design Precautions]

WARNING●Configure safety circuits externally to ensure that the entire system operates safely even when a fault occurs in the external power
supply, the programmable controller, or the products. Failure to do so may result in an accident due to an incorrect output or
malfunction.
(1) Emergency stop circuits, protection circuits, and protective interlock circuits for conflicting operations (such as
forward/reverse rotations or upper/lower limit positioning) must be configured externally.
(2) Outputs may remain on or off due to a failure of a component such as a relay, transistor, and triac used for digital signal
converter outputs. Configure an external circuit for monitoring output signals that could cause a serious accident.
●In an output circuit for digital signal converter outputs, when a load current exceeding the rated current or an overcurrent caused
by a load short-circuit flows for a long time, it may cause smoke and fire. To prevent this, configure an external safety circuit, suchas a fuse.
●Configure a circuit so that the programmable controller is turned on first and then the external power supply. If the external power
supply is turned on first, an accident may occur due to an incorrect output or malfunction.

[Design Precautions]

CAUTION●Do not install the control lines or communication cables together with the main circuit lines or power cables. Keep a distance of100mm (3.94 inches) or more between them. Failure to do so may result in malfunction or failure due to noise.
●When using a terminal block conversion module for a high-speed counter module, do not install the control lines or communication
cables together with the main circuit lines or power cables. Keep a distance of 150mm (5.91 inches) or more between them. Failure
to do so may result in malfunction or failure due to noise.
●Keep a distance of 100mm (3.94 inches) or more between a thermocouple or RTD (Resistance Temperature Detector) and themain circuit line or AC control lines. Also, keep the thermocouple or RTD away from a circuit that includes harmonics, such as ahigh-voltage circuit and a load circuit of an inverter. If not, the thermocouple or RTD is more likely to be affected by noise, surges,
and induction.
●At power-on or power-off, a voltage may occur or a current may flow between output terminals for a moment. To use an analog
signal converter or analog terminal block conversion module, start the control after analog outputs become stable.
●Do not place an analog signal converter or analog terminal block conversion module near a device that generates magnetic noise.
●When a device such as a lamp, heater, or solenoid valve is controlled using a module for digital signal converter outputs, a large
current (approximately 10 times greater than normal) may flow when the output is turned from off to on. Therefore, select a module
for digital signal converter outputs that has a sufficient current rating.

3

[Installation Precautions]

WARNING●Shut off the external power supply (all phases) used in the system before installation. Failure to do so may result in electric shock
or damage to the products.

[Installation Precautions]

CAUTION●Use products in an environment that meets the general specifications in this manual. Failure to do so may result in electric shock,fire, malfunction, or damage to or deterioration of the products.
●Securely fix the products with a DIN rail or screws. Incorrect installation may cause malfunction, failure, or drop of the module.
When using the products in an environment of frequent vibrations, fix the products with screws.
●Tighten the screws within the specified torque range. Undertightening can cause drop of the screw, short circuit, or malfunction.
Overtightening can damage the screw and/or products, resulting in drop, short circuit, or malfunction.
●Attach DIN rail stoppers on the right and left sides of the cable junction unit to fix the module securely.
●Shut off the external power supply (all phases) used in the system before mounting or removing the products. Failure to do so may
result in damage to, malfunction of, or failure of the products.
●Do not directly touch any conductive parts and electronic components of the products. Failure to do so may cause malfunction or
failure of the products.
●Install the products in the correct orientation if it is specified. Failure to do so may result in damage to or deterioration of the
products.
●When drilling screw holes, be careful not to drop chips into the inside of the products or conductive parts. Such foreign matter cancause a fire, failure, or malfunction.
●When using modules for replacing digital signal converters or signal conversion modules, use them in the correct combination.
Incorrect combination may cause failure.
●Shut off the power supply before installing/removing a module for replacing digital signal converters. Failure to do so may cause
failure or malfunction.
●Securely mount a module for replacing digital signal converters and signal conversion module on a digital signal converter andinstallation base. Failure to do so may cause damage to or drop of the products, or malfunction due to poor contact. Follow thecorrect procedure to install/remove them. Failure to do so may cause damage to or drop of the products, or malfunction due topoor contact.
●When a module for digital signal converters or signal conversion module is mounted on a digital signal converter or installationbase, hold the digital signal converter or installation base to transport them or install them to a panel. Holding the module for digital
signal converters or signal conversion module may cause drop or failure of the digital signal converter or installation base.

4

[Wiring Precautions]

WARNING●Shut off the external power supply (all phases) used in the system before wiring. Failure to do so may result in electric shock or
damage to the products.
●After wiring, attach the included terminal cover to the products before turning them on for operation. Failure to do so may result inelectric shock.

[Wiring Precautions]

CAUTION●Use applicable solderless terminals and tighten them within the specified torque range. Failure to do so may cause failure, damage,or malfunction.
●Check the rated voltage and terminal layout before wiring to the products, and connect the cables correctly. Connecting a power
supply with a different voltage rating or incorrect wiring may cause a fire or failure.
●Do not install the control lines or communication cables together with the main circuit lines or power cables. Keep a distance of100mm or more between them. Failure to do so may result in malfunction due to noise.
●When using a terminal block conversion module for a high-speed counter module, do not install the control lines or communication
cables together with the main circuit lines or power cables. Keep a distance of 150mm (5.91 inches) or more between them. Failure
to do so may result in malfunction or failure due to noise.
●Keep a distance of 100mm (3.94 inches) or more between a thermocouple or RTD (Resistance Temperature Detector) and themain circuit line or AC control lines. Also, keep the thermocouple or RTD away from a circuit that includes harmonics, such as ahigh-voltage circuit and a load circuit of an inverter. If not, the thermocouple or RTD is more likely to be affected by noise, surges,
and induction.
●Do not place an analog signal converter or analog terminal block conversion module near a device that generates magnetic noise.
●Place the cables in a duct or clamp them. If not, dangling cable may swing or inadvertently be pulled, resulting in damage to the
products or cables or malfunction due to poor contact.
●Tighten the terminal screws within the specified torque range. Undertightening can cause short circuit, fire, or malfunction.
Overtightening can damage the screw and/or products, resulting in drop, short circuit, or malfunction.
●Tighten the connector screws within the specified torque range. Undertightening can cause short circuit, fire, or malfunction.
Overtightening can damage the screw and/or products, resulting in drop, short circuit, fire, or malfunction.
●Securely connect connectors to the products. Failure to do so may cause malfunction.
●When disconnecting a cable from the products, do not pull the cable by the cable part. For the cable with connector, hold theconnector part of the cable. For the cable connected to the terminal block, loosen the terminal screw. Pulling the cable connectedto the products may result in malfunction or damage to the products or cable.
●Check the interface type and correctly connect the cable. Incorrect wiring (connecting the cable to an incorrect interface) may
cause failure of the products and external device.
●Prevent foreign matter such as dust or wire chips from entering the products. Such foreign matter can cause a fire, failure, or
malfunction.
●The products must be installed in control panels. Connect the main power supply to the products in the control panel through arelay terminal block. Wiring and replacement of the products must be performed by qualified maintenance personnel withknowledge of protection against electric shock.
●When connecting the products with a programmable controller, check that the product configuration is correct. An incorrect
configuration may cause failure or malfunction.
●Use the products with no force applied to their connectors. Applied force may cause failure or disconnection.
●Attach protective covers or signal conversion modules to unused connectors or empty slots of the products. Failure to do so may
cause a fire, failure, or malfunction due to foreign matter.
●When using modules for replacing digital signal converters or signal conversion modules, use them in the correct combination.
Incorrect combination may cause failure of a programmable controller, digital signal converter, installation base, or external device.
●Individually ground the FG terminal of the products with a ground resistance of 100 ohms or less. Failure to do so may result inelectric shock or malfunction.

5

[Startup and Maintenance Precautions]

WARNING●Do not touch any terminal while power is on. Doing so will cause electric shock or malfunction.
●Shut off the external power supply (all phases) used in the system before cleaning the products or retightening the terminal screws,
connector screws, or products fixing screws. Failure to do so may result in electric shock or cause failure or malfunction of the
products. Undertightening can cause drop of the screw, short circuit, or malfunction. Overtightening can damage the screw and/or
products, resulting in drop, short circuit, or malfunction.

[Startup and Maintenance Precautions]

CAUTION●Do not disassemble or modify the products. Doing so may cause failure, malfunction, injury, or a fire.
●Use any radio communication device such as a cellular phone or PHS (Personal Handy-phone System) more than 25cm away inall directions from the programmable controller and products. Failure to do so may cause malfunction.
●Shut off the external power supply (all phases) used in the system before mounting or removing the products. Failure to do so may
cause failure or malfunction of or damage to the products.
●After the first use of the products, do not connect/remove the products and cables more than 50 times. Exceeding the limit may
cause malfunction.
●Startup and maintenance of a control panel must be performed by qualified maintenance personnel with knowledge of protection
against electric shock. Lock the control panel so that only qualified maintenance personnel can operate it.
●This product displays the following symbol marks. This symbol mark indicates that this product is susceptible to static electricity.
Before handling the products, touch a conducting object such as a grounded metal to discharge the static electricity from thehuman body. Failure to do so may cause failure or malfunction of the products.

[Disposal Precautions]
CAUTION●When disposing of the products, treat them as industrial waste.

[Transportation Precautions]

CAUTION●Do not apply shock that exceeds the shock resistance described in the general specifications during transportation since theproducts are precision devices. Doing so may cause failure of the module.
●The halogens (such as fluorine, chlorine, bromine, and iodine), which are contained in a fumigant used for disinfection and pest
control of wood packaging materials, may cause failure of the products. Prevent the entry of fumigant residues into the product orconsider other methods (such as heat treatment) instead of fumigation. The disinfection and pest control measures must be applied
to unprocessed raw wood.

EMC and Low Voltage Directives
Compliance with the EMC Directive, which is one of the EU directives, has been mandatory for products sold within EU
member states since 1996 as well as compliance with the Low Voltage Directive since 1997.
For products compliant to the EMC and Low Voltage Directives, their manufacturers are required to declare complianceand affix the CE marking.
Sales representative in EU member states
The sales representative in EU member states is:Company: MITSUBISHI ELECTRIC EUROPE B.V.
Address: Mitsubishi-Electric-Platz 1, 40882 Ratingen, Germany

6安全注意事项
(使用之前请务必阅读)
使用本产品前，应仔细阅读本用户手册及综合目录中所介绍的关联手册，同时在充分注意安全的前提下正确地操作。
此外，该注意事项仅记载了与省配线·省工时设备的产品相关的内容。关于可编程控制器系统方面的安全注意事项，请参阅所使用的可编程控制器的用户手册。
在“安全注意事项”中，安全注意事项分为“警告”和“注意”两个等级。

警告表示错误操作可能造成危险后果，导致死亡或重伤事故。

注意表示错误操作可能造成危险后果，导致中度伤害、轻伤及设备损失。

注意根据情况不同，即使“注意”这一级别的事项也有可能引发严重后果。
两级注意事项记载的都是重要内容，请务必遵照执行。
【设计注意事项】

警 告● 应在外部设置安全电路，当外部电源异常或可编程控制器以及本产品故障时，能确保整个系统安全运行。误输出、误动作可能导
致事故。
(1) 应务必在外部配置紧急停止电路、保护电路、防止正转/反转等相反动作同时进行的互锁电路、防止超过定位上限/下限导致机械损坏的互锁电路等。
(2) 当数字信号转换器 输出用继电器、晶体管或触发三极管等发生故障时，输出可能保持为ON或OFF状态。对于可能引起重大事故
的输出信号，应在外部配置监视电路。
● 在数字信号转换器 输出用的输出电路中，因超过额定负载电流或负载短路等导致长时间持续过电流的情况下，可能引起冒烟或
着火，应在外部设置保险丝等安全电路。
● 应配置在可编程控制器本体电源接通以后方可接通外部供应电源的电路。如果先接通外部供应电源，误输出或误动作可能导致事故。

【设计注意事项】

注 意● 请勿将控制线及通信电缆与主电路及动力线等捆扎在一起，也不要相互靠得太近。应至少相距100mm。否则噪声可能导致误动作或故障。
● 使用高速计数器模块用端子排转换模块时，请勿将控制线及通信电缆与主电路及动力线等捆扎在一起，也不要相互靠得太近。应
至少相距150mm。否则噪声可能导致误动作或故障。
● 热电偶、测温电阻体必须与主电路线及交流控制电路线至少相距100mm。应与包含谐波的电路如高压电线或变频器的负载电路等
保持足够的距离。容易受到噪声、浪涌以及感应的影响。
● 在电源ON/OFF时，输出端子可能会有瞬间电压或瞬时电流流过。使用模拟信号转换器或模拟用端子排转换模块时，应在模拟输出稳定之后再开始进行控制。
● 请勿将模拟信号转换器、模拟用端子排转换模块安装在会发生磁性噪声的设备附近。
● 通过数字信号转换器 输出用控制灯负载、加热器、电磁阀等时，输出OFF→ON时可能有较大电流(通常的10倍左右)流过，因此应选择有充足额定电流的数字信号转换器 输出用产品。

7

【安装注意事项】

警 告● 进行安装作业时，必须将系统使用的外部供应电源全部断开之后再进行操作。否则可能触电或损伤产品。

【安装注意事项】

注 意● 应在本用户手册记载的一般规格环境下使用本产品。在不符合一般规格环境下使用时，可能导致触电、火灾、误动作以及产品损伤或劣化。
● 应使用DIN导轨或紧固螺栓将本产品牢固固定。如果未正确安装本产品，可能导致误动作、故障或脱落。在振动频繁的环境下使
用时，应用螺栓拧紧本产品。
● 应在规定的扭矩范围内拧紧螺栓。如果螺栓拧得过松，可能导致脱落、短路或误动作。如果螺栓拧得过紧，可能引起螺栓或本产
品破损，从而导致脱落、短路或误动作。
● 应将DIN导轨固定金属附件安装至电缆中继模块左右两侧，并且牢固固定。
● 拆装本产品时，必须将系统使用的外部供应电源全部断开之后再进行操作。否则可能导致产品损伤、误动作或故障。
● 请勿直接触摸本产品的导电部分及电子部件。否则有可能导致产品的误动作、故障。
● 指定了安装方向的情况下，应按照指定的安装方向进行安装。如果以指定外的方向安装，可能导致产品损伤或劣化。
● 进行螺栓孔加工时，应注意不要将切屑掉落到本产品内部或导电部位。否则可能导致火灾、故障或误动作。
● 应正确组合使用数字信号转换器更换用单元、信号转换单元。如果错误组合并使用可能导致故障。
● 拆装数字信号转换器更换用单元时，必须将电源全部断开之后再进行操作。否则可能导致故障或误动作。
● 应将数字信号转换器更换用单元、信号转换单元牢固地安装至数字信号转换器和基座上。如果未正确安装，可能因破损、脱落以
及接触不良导致误动作。此外应按照正确的步骤进行拆装。如果未正确拆装，可能因破损、脱落以及接触不良导致误动作。
● 在数字信号转换器用单元、信号转换单元安装在数字信号转换器、基座上的状态下进行搬运或安装至控制柜中时，应握住数字信号转换器和基座本体进行作业。否则可能导致数字信号转换器、基座脱落或故障。

【配线注意事项】

警 告● 进行配线作业时，必须将系统使用的外部供应电源全部断开之后再进行操作。否则可能触电或损伤产品。
● 配线作业后，在进行通电或运行时，必须安装产品附带的端子盖板。如果未安装端子盖板，可能导致触电。

8【配线注意事项】

注 意● 应使用合适的压装端子，并按规定的扭矩拧紧。如果未使用适用压装端子或扭矩超出规定，则可能导致故障、破损或误动作。
● 对本产品进行配线时，应在确认产品的额定电压及端子排列后再进行正确操作。如果输入的电压、连接的电源与额定值不符，或者配线错误，可能导致火灾或故障。
● 请勿将控制线及通信电缆与主电路及动力线等捆扎在一起，也不要相互靠得太近。应至少相距100mm。否则噪声可能导致误动作。
● 使用高速计数器模块用端子排转换模块时，请勿将控制线及通信电缆与主电路及动力线等捆扎在一起，也不要相互靠得太近。应
至少相距150mm。否则噪声可能导致误动作或故障。
● 热电偶、测温电阻体必须与主电路线及交流控制电路线至少相距100mm。应与包含谐波的电路如高压电线或变频器的负载电路等
保持足够的距离。容易受到噪声、浪涌以及感应的影响。
● 请勿将模拟信号转换器、模拟用端子排转换模块安装在会发生磁性噪声的设备附近。
● 本产品上连接的电线或电缆必须纳入导管中或通过夹具进行固定处理。如果未将电缆纳入导管中或未通过夹具进行固定处理，可能会由于电缆的晃动、移动、不经意的拉扯等导致本产品、电缆破损或因电缆连接不良导致误动作。
● 应在规定的扭矩范围内拧紧端子螺栓。如果端子螺栓拧得过松，可能导致短路、火灾或误动作。如果端子螺栓拧得过紧，可能引
起螺栓或本产品破损，从而导致脱落、短路或误动作。
● 应在规定的扭矩范围内拧紧连接器安装螺栓。如果螺栓拧得过松，可能导致短路、火灾或误动作。如果螺栓拧得过紧，可能引起螺栓或本产品破损，从而导致脱落、短路、火灾或误动作。
● 连接器应切实安装到本产品上。否则可能导致误动作。
● 拆卸本产品上连接的电缆时，请勿用手拉拽电缆部分。对于带有连接器的电缆，应握住与本产品相连接的连接器进行拆卸。对于
连接端子排的电缆，应将端子排端子螺栓松开后再进行拆卸。如果在与本产品相连接的状态下拉扯电缆，可能导致误动作、本产品或电缆破损。
● 连接电缆时，应在确认连接接口类型后，正确进行连接。如果连接到不同的接口上或配线错误，可能导致本产品、外部设备故
障。
● 注意请勿让切屑或配线头等异物混入本产品内部。否则可能导致火灾、故障或误动作。
● 应将本产品安装在控制盘内使用。对安装在控制盘内的本产品进行主电源配线时，应通过中继端子排连接。此外，进行本产品的更换及配线作业时，应由在触电保护方面受到过良好培训的维护人员进行操作。
● 与可编程控制器连接时，应确认产品配置正确。否则可能导致故障或误动作。
● 使用本产品时，请勿对连接器施力。否则可能导致故障或断线。
● 应在本产品的未使用连接器、空余插槽上安装保护盖板或信号转换单元。如果未安装盖板，可能因进入异物而导致火灾、故障以及误动作。
● 应正确组合使用数字信号转换器更换用单元、信号转换单元。否则可能导致可编程控制器、数字信号转换器、基座以及外部设备
故障。
● 必须对 FG 端子采用本产品专用接地(接地电阻不超过 100Ω)。否则可能导致触电或误动作。

9【启动·维护注意事项】

警 告● 请勿在通电状态下触摸端子。否则可能导致触电或误动作。
● 在清扫、重新紧固端子螺栓、连接器安装螺栓以及本产品固定螺栓时，必须将系统使用的外部供应电源全部断开之后再进行操作。否则可能触电或导致本产品故障或误动作。如果螺栓拧得过松，可能导致脱落、短路或误动作。如果螺栓拧得过紧，可能引
起螺栓或本产品破损，从而导致脱落、短路或误动作。

【启动·维护注意事项】

注 意● 请勿拆卸、改造本产品。否则可能导致故障、误动作、人员受伤或火灾。
● 使用便携电话或PHS等无线通信设备时，应在全方向与可编程控制器或本产品至少保持25cm的距离。否则可能导致误动作。
● 拆装本产品时，必须将系统使用的外部供应电源全部断开之后再进行操作。如果未全部断开，可能导致本产品故障、误动作以及损伤。
● 产品投入使用后，本产品或电缆等的拆装次数不应超过50次。如果超过50次，可能导致误动作。
● 进行控制盘内的启动、维护作业时，应由在触电保护方面受过良好培训的维护作业人员操作。此外，控制盘应上锁，以便只有维护作业人员才能操作控制盘。
● 本产品上贴有下述标志。该标志表示本产品容易受到静电的影响。在触摸本产品之前，必须先接触已接地的金属等导电体，释放掉人体所携带的静电。如果不释放掉静电，可能导致本产品故障或误动作。此外请勿在通电状态下触摸本产品。否则有可能因人
员受伤或人体的静电导致模块故障或误动作。

【废弃注意事项】

注 意● 废弃产品时，应将本产品作为工业废弃物处理。

【运输注意事项】

注 意● 本产品为精密设备，因此应避免在运输期间受到超出一般规格范围的冲击。否则可能导致故障。
● 如果木制包装材料的消毒及防虫措施的熏蒸剂中所包含的卤素物质(氟、氯、溴、碘等)侵入本公司产品，可能导致故障。应采取相应措施防止残留的熏蒸成分侵入本公司产品，或采用熏蒸以外的方法(热处理等)进行处理。此外，应对包装前的木材实施消毒及防
虫措施。

10

REVISIONS
Print Date
March, 2024

*Manual Number
50D-FG0785*The manual number is given on the bottom left of the last page.
RevisionFirst edition

This manual confers no industrial property rights or any rights of any other kind, nor does it confer any patent licenses. Mitsubishi
Electric Engineering cannot be held responsible for any problems involving industrial property rights which may occur as a result ofusing the contents noted in this manual.
© 2024 MITSUBISHI ELECTRIC ENGINEERING COMPANY LIMITED11

CONTENTS
SAFETY PRECAUTIONS ····································································· 2
EMC and Low Voltage Directives ························································· 6
REVISIONS ····················································································· 11
CONTENTS ····················································································· 12
1. INTRODUCTION ··········································································· 13
2. GENERAL SPECIFICATIONS·························································· 13
3. PERFORMANCE SPECIFICATIONS ················································· 14
3-1. FA1-MM40P，FA1-MM20P ······················································· 14
4. PARTS NAMES ············································································ 15
4-1. FA1-MM40P，FA1-MM20P ······················································· 15
5. CONNECTING METHOD ································································ 16
5-1.Connection example with the cable junction unit of a programmable controller. ····· 16
5-2.Connecting method ···································································· 17
6. MOUNTING DIRECTION································································· 18
7. EXTERNAL CONNECTION EXAMPLE ·············································· 19
8. CONNECTABLE MODULES ··························································· 20
8-1. MELSEC iQ-R series ································································ 21
8-2. MELSEC iQ-F series ································································ 27
8-3. MELSEC-Q series ··································································· 33
8-4. MELSEC-F series ···································································· 40
8-5. MELSEC-L series ···································································· 44
8-6. CC-Link IE TSN series ······························································ 48
8-7. CC-Link IE Field Basic series ····················································· 52
8-8. CC-Link IE Field series ····························································· 55
8-9. CC-Link series ········································································ 58
8-10. Other PLC ············································································ 61
9. EXTERNAL DIMENSIONS ······························································ 64
10. PRECAUTIONS ··········································································· 65
11. TROUBLESHOOTING ·································································· 65
12. GRATIS WARRANTY TERMS AND GRATIS WARRANTY RANGE ······ 66
13. EXCLUSION FROM LIABILITY FOR OPPORTUNITY LOSS AND SECONDARY LOSS····· 66
14. TRADEMARKS ··········································································· 66

121. INTRODUCTION
This manual describes the specifications and handling of the cable junction unit used in combination
with Mitsubishi Electric Corporation programmable controller modules.

2. GENERAL SPECIFICATIONS
ItemSpecifications

Operating ambient temperature
Storage ambient temperature
Operating ambient humidity
Storage ambient humidity-20 to 55 C
-25 to 75 C
5 to 95%RH, non-condensing
5 to 95%RH, non-condensing

Applicable standard
Underintermittent
Vibration
vibration
resistanceUnder
continuous
vibration
Shock resistanceOperating atmosphere
Operating altitude*1
Installation location
Overvoltage category*2
Pollution degree*3

5 to 8.4Hz
8.4 to 150Hz
Sweep count5 to 8.4Hz
8.4 to 150Hz
Sweep count

JIS B 3502:2011, IEC 61131-2:2007
Half amplitude: 3.5mm
Constant acceleration: 9.8m/s2 (1G)
10 times each in X, Y, and Z directions
Half amplitude: 1.75mm
Constant acceleration: 4.9m/s2 (0.5G)－
Compliant with JIS B 3502:2011 and IEC 61131-2:2007(147m/s2 (15G), 3 times each in X, Y, and Z bidirections)
No corrosive gases
2000m or lower
Inside a control panel*4, Indoor use
II or less2 or less*1: Do not use or store the products under pressure higher than the atmospheric pressure of altitude 0m. Doing so may cause malfunction.
*2: This category indicates the section of the power supply to which the equipment is assumed to be connected between the public
electrical power distribution network and the machinery within premises.
*3: This index indicates the degree to which conductive material is generated in terms of the environment in which the equipment is used.
*4: The enclosure is suitably designed for those specific environmental conditions, as applicable, and enclosure rate meets IP20 andminimum type 1 of UL 50.

133. PERFORMANCE SPECIFICATIONS
3-1. FA1-MM40P，FA1-MM20P
Model
Item
Number of points
Rated voltage
Maximum usage voltage
Maximum usage current
Number of connectable modules
Maximum length of the line
Installation
DIN rail
methodWithstand voltage
Insulation resistance (initial)
Weight

FA1-MM40P
40 points

FA1-MM20P

20 points
24VDC
30VDC
Signal : 1A
2
20m
Applicable DIN rail: TH 35-7.5 Fe, TH 35-7.5 Al(IEC60715 compliant)
1250VAC for 1minutes
10MΩ or more by 500VDC insulation resistance tester
Approx. 44g
Approx. 38g

14

4. PARTS NAMES
4-1. FA1-MM40P，FA1-MM20P

No.

Name

(1)

Connector for cable connection

(2)
(3)

Fixed hook
DIN rail hook

Description
This connector is used to connect the cable.
Model
Number of points
FA1-MM40P
40 points
FA1-MM20P
20 points
This hook is for attaching this product to the DIN rail.
This hook is for attaching this product to the DIN rail.

15

5. CONNECTING METHOD
5-1.Connection example with the cable junction unit of a programmable controller.
(1) FA1-MM40P(2) FA1-MM20P

16

5-2. Connecting method
5-2-1. Installing/removing the module to a DIN rail
(1)

Installing① Place the DIN rail installing groove onto the DIN rail to hook the module.
② Press the module against the DIN rail until it clicks.

①

DIN rail②Press(2)

Removing① Insert a flat-blade screwdriver into the DIN rail hook.
② Move the DIN rail hook downward.
③ Remove from the Din rail.

③

②

①

17

6. MOUNTING DIRECTION
No mounting direction specified.
Use this product by attaching it to a DIN rail.

18

7. EXTERNAL CONNECTION EXAMPLE(1)

FA1-MM40P
40

40
39

39

38

38
37

37

36

36
35

35

34

CON1

34
33

40

39

32

32
31

31

30
29

39

2

1

29
28

27

27

26

26
25

25

24

24
23

1

40

30

28

2

CON2
33

23

22

22
21

21

20

20
19

19

18

18
17

17

16

16
15

15

14

14
13

13

12

12
11

11

10

10
9

9

8

8
7

7

6

6
5

5

4

4
3

3

2

2
1

1
1A／pin(2)

FA1-MM20P
20

20
19

CON1

19

18

18
17

20

19

16
15

15

14
13

19

2

1

13
12

11

11

10

1

20

14

12

2

CON2

17

16

10
9

9

8

8
7

7

6

6
5

5

4

4
3

3

2

2
1

1
1A／pin19

8. CONNECTABLE MODULES

Reference

Programmable controller

8-1.

MELSEC iQ-R series

8-2.

MELSEC iQ-F series

8-3.

MELSEC-Q series

8-4.

MELSEC-F series

8-5.

MELSEC-L series

8-6.

CC-Link IE TSN series

8-7.

CC-Link IE Field Basic series

8-8.

CC-Link IE Field series

8-9.

CC-Link series

8-10.

Other PLC

20

8-1. MELSEC iQ-R series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

RX40C7

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

Negative common Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

Positive common

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**FM2V

FA1-TH8X2SC20S1E

FA-CBL**FM2LV

FA1-TH4X24RA1L20S1E

FA-CBL**M20

FA1-TH8X24RA1L20S1E

FA-CBL**YM20

FA1-TH16X24RA1L20S1E

FA-CBL**TMV20

FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Negative common Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
RX40C7-TS

Positive common

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E

Negative common Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
RX40NC6B

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

21

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

RX41C4

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

Junction terminal block FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMVE

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Positive common

RX41C6HS

FA1-TESV32XY

RX42C4

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**FM2V

FA1-TH8X2SC20S1E

FA-CBL**FM2LV

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Negative common Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40P

22

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

RX41C4-TS

Junction terminal block FA1-TE2SV16XY

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

Positive common

FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
Negative common Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
RX70C4

Positive common

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Negative common Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
RX71C4

Positive common

Junction terminal block FA1-TE2SD32XY

RX72C4

FA1-TESV32XY

RX61C6HS

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

23

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FA-CBL**FMVE

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

RX71C4

Negative common Junction terminal block FA1-TE2SD32XY

RX72C4

FA1-TESV32XY

RX61C6HS

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40P

RY40NT5P

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-TH8Y2SC20S1E

FA-CBL**YM20

FA1-TH16Y2SC20S1E

FA-CBL**TMV20

FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
RY40NT5P-TS

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

RY40PT5P

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

RY40PT5B

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

24

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

RY40PT5P

Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

RY40PT5B

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20

FA1-TH1E16Y2SC20S1E

FA-CBL**TMV20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
RY40PT5P-TS

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

RY41NT2P

Junction terminal block FA1-TE2SD32XY

RY42NT2P

FA1-TESV32XY

RY41NT2H

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**FM2V

FA1-TH8Y2SC20S1E

FA-CBL**FM2LV

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
Junction terminal block FA1-TE2SD40P

FA-CBL**FMV-M

FA-TBS40P

25

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

RY41NT2P-TS

Junction terminal block FA1-TE2SV16XY

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

FA1-CB1L**EM2F34

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
RY41PT1P

Junction terminal block FA1-TE2SD32XY

RY42PT1P

FA1-TESV32XY

RY41PT2H

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**FM2V

FA1-TH1E8Y2SC20S1E

FA-CBL**FM2LV

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
Junction terminal block FA1-TE2SD40P
FA-TBS40P
RY41PT1P-TS

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

RH42C4NT2P

For the input side, refer to the specifications of the RX41C4. For the output side, refer to the specifications of the RY41NT2P.

26

8-2. MELSEC iQ-F series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX5UC-32MT/D

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

Sink input

FX5-C32ET/D

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH4X2SC20S1E

FA-FXCBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Sink output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH4Y2SC20S1E

FA-FXCBL**MMH20

FA1-TH8Y2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20S
I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y
FA2-CB1LT**MM2H16X16Y

FX5-C32ET/DS-TS

Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E

Source input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Sink output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

FX5-C32ET/DSS-TS Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E

Source input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

27

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX5UC-64MT/D

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

Sink input

FX5UC-96MT/D

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4X2SC20S1E

FA-FXCBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Sink output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32Y

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4Y2SC20S1E

FA-FXCBL**MMH20

FA1-TH8Y2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20S
I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y
FA2-CB1LT**MM2H16X16Y

FX5-C16EX/D

Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH4X2SC20S1E

FA-FXCBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX5-C32EX/D

Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

28

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX5-C32EX/D

Digital signal converter FA1-TH4X2SC20S1E

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Sink input

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX5-C16EYT/D

Sink output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH4Y2SC20S1E

FA-FXCBL**MMH20

FA1-TH8Y2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20S
FX5-C32EYT/D

Sink output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32Y

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4Y2SC20S1E

FA-FXCBL**MMH20

FA1-TH8Y2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20SFX5UC-32MT/DSS

Source input

FX5-C32ET/DSS

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH4X2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Source output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY

29

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX5UC-32MT/DSS

Digital signal converter FA1-TH1E4Y2SC20S1E

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA1-TH1E8Y2SC20S1E

FA2-CB1LT**MM1H20E

FA1-MM40P

FA-CBL**MMH

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

Source output

FX5-C32ET/DSS

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y
FA2-CB1LT**MM2H16X16Y

FX5UC-32MT/DS-TS Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH16X24RA1L20S1E
FA1-TH16X24RA1H20S1E

Source input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Sink output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Sink output

Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

FX5UC-32MT/DSS-

Sink input

TS

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH16X24RA1L20S1E
FA1-TH16X24RA1H20S1E

Source input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

FX5UC-64MT/DSS

Source input

FX5UC-96MT/DSS

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4X2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

30

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX5UC-64MT/DSS

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

Source output

FX5UC-96MT/DSS

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32Y

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH1E4Y2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH1E8Y2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y
FA2-CB1LT**MM2H16X16Y

FX5-C16EX/DS

Source input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH4X2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX5-C32EX/DS

Source input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4X2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

31

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX5-C32EX/DS-TS

Junction terminal block FA1-TE2SV16XY

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**EM1F18E

FA1-MM20P

FA-CBL**MMH20

Sink input

FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH16X24RA1L20S1E
FA1-TH16X24RA1H20S1E
Source input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

FX5-C16EYT/DSS

Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
Digital signal converter FA1-TH1E4Y2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH1E8Y2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
FX5-C32EYT/DSS

Source output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32Y

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH1E4Y2SC20S1E

FA2-CB1L**MM1H20E

FA1-TH1E8Y2SC20S1E

FA2-CB1LT**MM1H20E

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
FX5-C32EYT/D-TS

Sink output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

FX5-C32EYT/DSSTS

Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

32

8-3. MELSEC-Q series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

QX40

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

Positive common

QX40-S1

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-TH8X2SC20S1E

FA-CBL**YM20

FA1-TH4X24RA1L20S1E

FA-CBL**TMV20

FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
QX41

Positive common

Junction terminal block FA1-TE2SD32XY

QX42

FA1-TESV32XY

QX41-S1

FA1-TE1S32XY

QX41-S2

FA-TB32XY

QX42-S1

FA-TBS32XY
FA-TB32XYL
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

33

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

QX41

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

QX42

FA1-TH8X2SC20S1E

FA-CBL**FM2LV

QX41-S1

FA1-TH4X24RA1L20S1E

QX41-S2

FA1-TH8X24RA1L20S1E

QX42-S1

FA1-TH16X24RA1L20S1E

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

Positive common

FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40P

QX70

Positive common

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Negative common Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
QX71
QX72

Positive common

Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

34

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FA-CBL**FMVE

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Negative common Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA-CBL**DMFX

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMVE

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

QX71

Negative common Junction terminal block FA1-TE2SD32XY

QX72

FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40P

QX80

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
QX81
QX81-S2

Negative common Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

QX82
QX82-S1

Negative common Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYP3

35

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FA-CBL**FMVE

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

QX82
QX82-S1

Negative common Junction terminal block FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SD40P
FA-TBS40P

QY40P

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

QY50

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-TH8Y2SC20S1E

FA-CBL**YM20

FA1-TH16Y2SC20S1E

FA-CBL**TMV20

FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
QY41P

Junction terminal block FA1-TE2SD32XY

QY41H

FA1-TESV32XY

QY42P

FA1-TE1S32XY

FA-CBL**FMV

FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

36

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

QY41P

Junction terminal block FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

QY41H

FA1-TE1SV16XY

FA-CBL**FM2LV

QY42P

FA-TB16XY

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM40P

FA-CBL**MMH

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**FM2V

FA1-TH8Y2SC20S1E

FA-CBL**FM2LV

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
Junction terminal block FA1-TE2SD40P
FA-TBS40P
QY70

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
QY71

Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
FA1-TE2SD40P

FA-CBL**FMV-M

FA-TBS40P

37

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

QY80

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY

FA-CBL**TMV20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**DMFY

FA1-MM40P

FA-CBL**MMH

FA-CBL**DM2FY

FA1-MM20P

FA-CBL**MMH20

FA-CBL**DM2FY

FA1-MM20P

FA-CBL**MMH20

FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20

FA1-TH1E16Y2SC20S1E

FA-CBL**TMV20

FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
QY81P

Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY
FA1-TE1SV16XY
FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

38

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

QY82P

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**FM2V

FA1-TH1E8Y2SC20S1E

FA-CBL**FM2LV

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
Junction terminal block FA1-TE2SD40P

FA-CBL**FMV-M

FA-TBS40P
QH42P

For the input side, refer to the specifications of the QX41. For the output side, refer to the specifications of the QY41P.

QX41Y41P

39

8-4. MELSEC-F series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX3GC-32MT/D

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Sink input

FX3UC-16MT/D

FA1-TE1SV16XY

FX3UC-32MT/D

FA-FXTB16XY

FX3UC-32MT-LT
FX3UC-32MT-LT-2
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Sink output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20SFX3UC-64MT/D

I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y

FA1-MM40P

FA-CBL**MMH

Sink input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MM2H16X16Y

FA1-MM40P

FA-CBL**MMH

FX3UC-96MT/D

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32X

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4X2SC20S1E

FA-FXCBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Sink output

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-TE1SV16XY

FA2-CB1LT**MM1H20

FA-FXTB16XY
FA-FXTB32Y

FA-FXCBL**MM2H
FA2-CB1LT**MM2H

Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20S
I/O combined

Junction terminal block FA-FXTB16X16Y

40

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX2NC-16EX

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MM2H

FA1-MM40P

FA-CBL**MMH

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Sink input

FA1-TE1SV16XY
FA-FXTB16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX2NC-32EX

Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY
FA-FXTB32X
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX2NC-16EX-DS

Sink input

FX2NC-32EX-DS

Digital signal converter FA1-TH4X2SC20S1E

FA-FXCBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX2NC-16EYT

Sink output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20S

41

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX2NC-32EYT

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MM2H

FA1-MM40P

FA-CBL**MMH

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Digital signal converter FA1-TH4X2SC20S1E

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA2-CB1LT**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

Sink output

FA1-TE1SV16XY
FA-FXTB16XY
FA-FXTB32Y
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-FXTH16YRA20
FA-FXTH16YRA11S
FA-FXTH16YRA20S
FX3GC-32MT/DSS

Source input

FX3UC-16MT/DSS

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

FX3UC-32MT/DSS

FA-FXTB16XY
Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

FX3UC-64MT/DSS

I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y

FA1-MM40P

FA-CBL**MMH

Source input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MM2H

FA1-MM40P

FA-CBL**MMH

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FX3UC-96MT/DSS

FA1-TE1SV16XY
FA-FXTB16XY
FA-FXTB32X
Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY

FA-FXCBL**MM2H

FA1-MM40P

FA-CBL**MMH

Digital signal converter FA1-TH4X2SC20S1E

FA-FXTB32X

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S

FA2-CB1L**MM1H20E

FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

42

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

FX3UC-64MT/DSS

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MM2H

FA1-MM40P

FA-CBL**MMH

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

Source output

FX3UC-96MT/DSS

FA1-TE1SV16XY
FA-FXTB16XY
FA-FXTB32Y
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

FX2C-16EX-DS

I/O combined

Junction terminal block FA-FXTB16X16Y

FA-FXCBL**MM2H16X16Y

FA1-MM40P

FA-CBL**MMH

Source input

Junction terminal block FA1-TE2SV16XY

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Digital signal converter FA1-TH4X2SC20S1E

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA2-CB1LT**MM1H20E

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-FXCBL**MM2H

FA1-MM40P

FA-CBL**MMH

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY
FA-FXTB16XY
Sink input

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY

FA1-TH16X24RA1L20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
FX2NC-16EYT-DSS

Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

FX2NC-32EYT-DSS

Source output

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
FA-FXTB16XY
FA-FXTB32Y
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

43

8-5. MELSEC-L series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

LX40C6

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

Positive common

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-TH8X2SC20S1E

FA-CBL**YM20

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Negative common Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-TE1SV16XY

FA-CBL**YM20

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
LX41C4
LX42C4

Positive common

Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

44

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

LX41C4

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA-CBL**FM2LV

FA-CBL**FMVE

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA1-MM20P

FA-CBL**MMH20

Positive common

LX42C4

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
Negative common Junction terminal block FA1-TE2SD32XY
FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40P

LY40NT5P

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-TH8Y2SC20S1E

FA-CBL**YM20

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20

45

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

LY40PT5P

Junction terminal block FA1-TE2SV16XY

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**YM20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
LY41NT1P

Junction terminal block FA1-TE2SD32XY

LY42NT1P

FA1-TESV32XY
FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**FM2V

FA1-TH8Y2SC20S1E

FA-CBL**FM2LV

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
Junction terminal block FA1-TE2SD40P

FA-CBL**FMV-M

FA-TBS40P

46

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

LY41PT1P

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

LY42PT1P

FA1-TESV32XY

FA1-TE2SV16XY

FA-CBL**FM2V

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY

FA-CBL**FM2LV

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYH
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**FM2V

FA1-TH1E8Y2SC20S1E

FA-CBL**FM2LV

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
Junction terminal block FA1-TE2SD40P

FA-CBL**FMV-M

FA-TBS40P
LH42C4NT1P

For the input side, refer to the specifications of the LX41C4.For the output side, refer to the specifications of the LY41NT1P.

LH42C4PT1P

For the input side, refer to the specifications of the LX41C4.For the output side, refer to the specifications of the LY41PT1P.

L02SCPU

Junction terminal block FA1-TE2SD40P

L02SCPU-P

FA-CBL**FMV-M

FA-TBS40P

L02CPU
L02CPU-P
L06CPU
L06CPU-P
L26CPU
L26CPU-P
L26CPU-BT
L26CPU-PBT

47

FA1-MM40P

FA-CBL**MMH

8-6. CC-Link IE TSN series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GN2B1-32D

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA-CBL**YM20

FA3-CB1L**EM1F18X

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM1F18X

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM1F18Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM1F18Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM1F18Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM1F18Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34X

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34X

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

Positive common

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
NZ2GN2S1-16D

Positive common

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E

NZ2GN2S1-16T

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

NZ2GN2S1-16TE

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

NZ2GN2S1-32D

Positive common

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E

NZ2GN2S1-32T

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

NZ2GN2S1-32TE

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

48

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GN2S1-32DT

Junction terminal block FA1-TE2SV16XY

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA1-TESV32XY

FA-FCBL**FMH

FA1-MM20P

FA-CBL**MMH20

Input side

FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
Output side

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E

NZ2GN2S1-32DTE

Input side

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Output side

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E

NZ2GNCF1-32D

Positive common

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY

FA-CBL**FM2H

FA1-TE1SV16XY

FA-CBL**FM2LH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

49

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GNCF1-32D

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**FM2H

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA-CBL**FM2LH

FA-CBL**FMH-M

FA1-MM40P

FA-CBL**MMH

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH8Y2SC20S1E

FA-CBL**YM20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

Positive common

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40PNZ2GN2B1-32T

Sink output

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
NZ2GNCF1-32T

Sink output

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMH

FA1-TESV32XY

FA-FCBL**FMH

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY

FA-CBL**FM2H

FA1-TE1SV16XY

FA-CBL**FM2LH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

50

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GNCF1-32T

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**FM2H

FA1-MM20P

FA-CBL**MMH20

FA1-TH8Y2SC20S1E

FA-CBL**FM2LH

FA1-MM40P

FA-CBL**MMH

Sink output

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
CommonJunction terminal block FA1-TE2SD40P

FA-CBL**FMH-M

FA-TBS40PNZ2GN2B1-32DT

I/O combined

For the input side, refer to the specifications of the NZ2GN2B1-32D. For the output side, refer to the specifications of the NZ2GN2B1-32T.

NZ2GN2B1-32TE

Source output

Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20

FA1-MM20P

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20SNZ2GN2B1-32DTE

I/O combined

The input side cannot be used. For the output side, refer to the specifications of the NZ2GN2B1-32TE.

51

FA-CBL**MMH20

8-7. CC-Link IE Field Basic series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2MFB1-32D

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA-CBL**YM20

FA1-MM20P

FA-CBL**MMH20

Positive common

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
NZ2MFB1-32T

Sink output

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-TH8Y2SC20S1E

FA-CBL**YM20

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
NZ2MFB1-32DT

I/O combined

For the input side, refer to the specifications of the NZ2MFB1-32D. For the output side, refer to the specifications of the NZ2MFB1-32T.

NZ2MFB1-32TE1

Source output

Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20

FA1-MM20P

FA-CBL**MMH20

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
NZ2MFB1-32DTE1

I/O combined

The input side cannot be used. For the output side, refer to the specifications of the NZ2MFB1-32TE1.

NZ2MF2S1-32D

Positive common

Junction terminal block FA1-TE2SV16XY

FA3-CB1L**EM2F34X

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34X

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

52

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2MF2S1-32T

Junction terminal block FA1-TE2SV16XY

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
NZ2MF2S1-32TE1

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

NZ2MF2S1-32DT

Input side

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

53

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2MF2S1-32DT

Junction terminal block FA1-TE2SV16XY

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

FA3-CB1L**EM2F34Y

FA1-MM20P

FA-CBL**MMH20

Output side

FA1-TE1SV16XY
Digital signal converter FA1-TH4Y2SC20S1E
FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
NZ2MF2S1-32DTE1 Input side

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY

Output side

Junction terminal block FA1-TE2SV16XY
FA1-TE1SV16XY
Digital signal converter FA1-TH1E4Y2SC20S1E
FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

54

8-8. CC-Link IE Field series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GF2B1N1-16D

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA-CBL**YM20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

Positive common

NZ2GF2B1-32D

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
NZ2GFCF1-32D

Positive common

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMH

FA1-TESV32XY

FA-FCBL**FMH

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY

FA-CBL**FM2H

FA1-TE1SV16XY

FA-CBL**FM2LH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**FM2H

FA1-TH8X2SC20S1E

FA-CBL**FM2LH

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S

FA-CBL**M20

FA-TH16X24D31

FA-CBL**YM20

FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
CommonJunction terminal block FA1-TE2SD40P

FA-CBL**FMH-M

FA-TBS40P

55

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GF2B1N1-16T

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH8Y2SC20S1E

FA-CBL**YM20

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

Sink output

NZ2GF2B1-32T

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
NZ2GFCF1-32T

Sink output

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMH

FA1-TESV32XY

FA-FCBL**FMH

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY

FA-CBL**FM2H

FA1-TE1SV16XY

FA-CBL**FM2LH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

56

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

NZ2GFCF1-32T

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**FM2H

FA1-MM20P

FA-CBL**MMH20

FA1-TH8Y2SC20S1E

FA-CBL**FM2LH

FA1-MM40P

FA-CBL**MMH

Sink output

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
CommonJunction terminal block FA1-TE2SD40P

FA-CBL**FMH-M

FA-TBS40PNZ2GF2B1-32DT

I/O combined

NZ2GFCF1-32DT

I/O combined

For the input side, refer to the specifications of the NZ2GF2B1N1-16D. For the output side, refer to the specifications of the NZ2GF2B1N116T.
Junction terminal block FA-TB16X16Y

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH-M

FA1-MM40P

FA-CBL**MMH

Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20(Positive common only for input)

FA-FCBL**FMH

FA1-TE2SD40P
FA-TBS40PNZ2GF2B1N1-16TE

Source output

NZ2GF2B1-32TE

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
NZ2GF2B1-32DTE

I/O combined

The input side cannot be used. For the output side, refer to the specifications of the NZ2GF2B1N1-16TE.

57

8-9. CC-Link series
①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

AJ65SBTB1-16D

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

AJ65SBTB1-16D1

FA1-TH8X2SC20S1E

FA-CBL**YM20

AJ65SBTB3-16D

FA1-TH4X24RA1L20S1E

AJ65SBTB3-16KD

FA1-TH8X24RA1L20S1E

AJ65SBTB1-32D

FA1-TH16X24RA1L20S1E

AJ65SBTB1-32D1

FA1-TH4X24RA1H20S1E

AJ65SBTB1-32KD

FA1-TH8X24RA1H20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA1-TESV32XY

FA-FCBL**FMH

FA1-MM20P

FA-CBL**MMH20

Positive common

FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
AJ65VBTS3-16D

Positive common

Digital signal converter FA1-TH4X2SC20S1E
FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

AJ65SBTCF1-32D

Positive common

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYN3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1N
FA-TB16XY2N
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY

FA-CBL**FM2H

FA1-TE1SV16XY

FA-CBL**FM2LH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D

58

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

AJ65SBTCF1-32D

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH8X2SC20S1E

FA-CBL**YM20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**FMH-M

FA1-MM40P

FA-CBL**MMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Positive common

FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S

FA-CBL**FM2H

FA-TH16X24D31

FA-CBL**FM2LH

FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L
CommonJunction terminal block FA1-TE2SD40P
FA-TBS40P

AJ65SBTB1-16T

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

AJ65SBTB1-16T1

Sink output

FA1-TH8Y2SC20S1E

FA-CBL**YM20

AJ65SBTB2-16T

FA1-TH16Y2SC20S1E

AJ65SBTB2-16T1

FA1-TH16Y2RA20S1E

AJ65SBTB1-32T

FA1-TH16Y1SR20S1E

AJ65SBTB1-32T1

FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20

AJ65VBTS2-16T

Sink output

Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**M20

FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20

59

①

②

③

④

⑤

Programmable controller

Junction terminal block or Digital signal converter

Cable

Cable junction unit

Cable

AJ65SBTCF1-32T

Junction terminal block FA1-TE2SD32XY

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA1-TESV32XY

FA-FCBL**FMH

FA1-MM20P

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA1-MM40P

FA-CBL**MMH

Sink output

AJ65BTC1-32T

FA1-TE1S32XY
FA-TB32XY
FA-TBS32XY
FA-TB32XYL
FA-TB32XYP3FA-TB8XY1
FA-TB8XY2
FA-TB8XY3
FA-TB8XY4
FA-TB16XY1
FA-TB16XY2
FA-CB8XY1
FA-CB8XY2
FA-CB8XY3
FA-CB8XY4FA-CB16XY1
FA-CB16XY2
FA-LEB32XY
FA-LEB32XY-3
FA-LEB32XY-3A
FA1-TE2SV16XY

FA-CBL**FM2H

FA1-TE1SV16XY

FA-CBL**FM2LH

FA-TB16XY
FA-TB16XYPN
FA-TB16XYPN3
FA-LEB16XY
FA-LEB16XY-D
Digital signal converter FA1-TH4Y2SC20S1E

FA-CBL**FM2H

FA1-TH8Y2SC20S1E

FA-CBL**FM2LH

FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20
CommonJunction terminal block FA1-TE2SD40P

FA-CBL**FMH-M

FA-TBS40P
AJ65SBTB1-32DT

I/O combined

For the input side, refer to the specifications of the AJ65SBTB1-16D. For the output side, refer to the specifications of the AJ65SBTB1-16T.

AJ65SBTCF1-32DT

I/O combined

Junction terminal block FA-TB16X16Y

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH-M

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMV-M

FA1-MM40P

FA-CBL**MMH

Digital signal converter FA1-TH1E4Y2SC20S1E

FA-CBL**M20

FA1-MM20P

FA-CBL**MMH20

FA1-TH1E8Y2SC20S1E

FA-CBL**YM20(Positive common only for input)

FA-FCBL**FMH

FA1-TE2SD40P
FA-TBS40P
AJ65VBTCF1-32DT1 I/O combined

Junction terminal block FA-TB16X16Y(Positive common only for input)
FA1-TE2SD40P
FA-TBS40P

AJ65SBTB1-16TE

Source output

AJ65SBTB1-32TE1

FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S
AJ65SBTB1-32DTE1 I/O combined

The input side cannot be used. For the output side, refer to the specifications of the AJ65SBTB1-16TE.

60

8-10. Other PLC
ASLINK TERMINAL series manufactured by Anywire
①

②

③

④

⑤

Programmable controller

Digital signal converter

Cable

Cable junction unit

Cable

BL265SB-16F-2-20

Digital signal converter FA1-TH4X2SC20S1E

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

FA2-CB1L**MM1H20E

FA1-MM20P

FA-CBL**MMH20

FA-CBL**MMH20

FA1-MM20P

FA-CBL**MMH20

Positive common

BL265SB-32F-2-20

FA1-TH8X2SC20S1E
FA1-TH4X24RA1L20S1E
FA1-TH8X24RA1L20S1E
FA1-TH16X24RA1L20S1E
FA1-TH4X24RA1H20S1E
FA1-TH8X24RA1H20S1E
FA1-TH16X24RA1H20S1E
FA-TH16XRA20S
FA-TH16X24D31
FA-TH16X24D31L
FA-TH16X48D31L
FA-TH16X100D31L
FA-TH16X100A31
FA-TH16X100A31L
FA-TH16X200A31
FA-TH16X200A31L

BL265PB-16F-2-20

Sink output

Digital signal converter FA1-TH4Y2SC20S1E

BL265PB-32F-2-20

FA1-TH8Y2SC20S1E
FA1-TH16Y2SC20S1E
FA1-TH16Y2RA20S1E
FA1-TH16Y1SR20S1E
FA1-TH16Y1TR20S1E
FA-TH16YRA11
FA-TH16YRA21
FA-TH16YRA20
FA-TH16YRA11S
FA-TH16YRA21S
FA-TH16YRA20S
FA-TH16YRA20SL
FA-TH16YRAB20SL
FA-TH16YRAC20S
FA-TH16YSR11S
FA-TH16YSR21S
FA-TH16YSR20S
FA-TH16YTL11S
FA-TH16YTL21S
FA-TH16YTH11S
FA-TH16YTR20S
FA-TH16Y2TR20

BL265PB-16FS-2-20 Source output

Digital signal converter FA1-TH1E4Y2SC20S1E

BL265PB-32FS-2-20

FA1-TH1E8Y2SC20S1E
FA1-TH1E16Y2SC20S1E
FA1-TH1E16Y2RA20S1E
FA1-TH1E16Y1SR20S1E
FA1-TH1E16Y1TR20S1E
FA1-TH1E16Y2RA20S
FA-THE16YTH11S
FA-THE16YTR20S

BL265XB-32F-2-20

I/O combined

For the input side, refer to the specifications of the BL265SB-16F-2-20. For the output side, refer to the specifications of the BL265PB-16F-220.

61

PLC modules manufactured by OMRON : CJ1/CJ1MCS series
①

②

③

④

⑤

Programmable controller

Junction terminal block

Cable

Cable junction unit

Cable

CJ1W-ID231

Junction terminal block FA1-TE2SD40P

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

Input

CJ1W-ID261
CJ1W-ID232

FA-TBS40P
Input

Junction terminal block FA1-TE2SD40P

CJ1W-ID262

FA-TBS40P

CJ1W-ID233
CJ1W-OD231

OutputJunction terminal block FA1-TE2SD40P

CJ1W-OD261
CJ1W-OD232

FA-TBS40P
OutputJunction terminal block FA1-TE2SD40P

CJ1W-OD233

FA-TBS40P

CJ1W-OD262
CJ1W-OD263
CJ1W-OD234
CJ1W-MD261

I/O combined

Junction terminal block FA1-TE2SD40P
FA-TBS40P

CJ1W-MD263

I/O combined

Junction terminal block FA1-TE2SD40P

CJ1W-MD563

FA-TBS40P

PLC modules manufactured by OMRON : CS series(CS1G/H, CS1D)
①

②

③

④

⑤

Programmable controller

Junction terminal block

Cable

Cable junction unit

Cable

CS1W-ID231

Junction terminal block FA1-TE2SD40P

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

Input

CS1W-ID261
CS1W-OD231

FA-TBS40P
OutputJunction terminal block FA1-TE2SD40P

CS1W-OD232

FA-TBS40P

CS1W-OD261
CS1W-OD262
CS1W-MD261

I/O combined

Junction terminal block FA1-TE2SD40P

CS1W-MD262

FA-TBS40P

CS1W-MD561

PLC modules manufactured by OMORON : DeviceNet
①

②

③

④

⑤

Programmable controller

Junction terminal block

Cable

Cable junction unit

Cable

GT1-ID32ML

Junction terminal block FA1-TE2SD40P

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

Input

GT1-ID32ML-1
DRT2-ID32ML

FA-TBS40P
Input

Junction terminal block FA1-TE2SD40P

DRT2-ID32ML-1
GT1-OD32ML

FA-TBS40P
OutputJunction terminal block FA1-TE2SD40P

GT1-OD32ML-1
DRT2-OD32ML

FA-TBS40P
OutputJunction terminal block FA1-TE2SD40P

DRT2-OD32ML-1
DRT2-MD32ML

FA-TBS40P
I/O combined

Junction terminal block FA1-TE2SD40P

DRT2-MD32ML-1

FA-TBS40P

PLC modules manufactured by OMORON : CompoBus/S
①

②

③

④

⑤

Programmable controller

Junction terminal block

Cable

Cable junction unit

Cable

SRT2-ID32ML

Junction terminal block FA1-TE2SD40P

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

FA-CBL**MMH-R

FA1-MM40P

FA-CBL**MMH

Input

SRT2-ID32ML-1
SRT2-OD32ML

FA-TBS40P
Output

SRT2-OD32ML-1
SRT2-MD32ML
SRT2-MD32ML-1

Junction terminal block FA1-TE2SD40P
FA-TBS40P

I/O combined

Junction terminal block FA1-TE2SD40P
FA-TBS40P

62

PLC modules manufactured by Yokogawa Electric : FA-M3 series
①

②

③

④

⑤

Programmable controller

Junction terminal block

Cable

Cable junction unit

Cable

F3XD32-3F

Junction terminal block FA1-TE2SD40P

FA-CBL**FMH-FY

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH-FY

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH-FY

FA1-MM40P

FA-CBL**MMH

Input

F3XD32-4F

FA-TBS40P

F3XD32-5F
F3XD64-3F
F3XD64-4F
F3XD64-6M
F3YD32-1H

OutputJunction terminal block FA1-TE2SD40P

F3YD32-1P

FA-TBS40P

F3YD32-1R
F3YD32-1T
F3YD64-1M
F3YD64-1P
F3YD64-1R
F3WD64-3P

I/O combined

Junction terminal block FA1-TE2SD40P

F3WD64-4P

FA-TBS40P

PLC modules manufactured by Fuji Electric FA Component & Systems : SPH series
①

②

③

④

⑤

Programmable controller

Junction terminal block

Cable

Cable junction unit

Cable

NP1X3206-W

Junction terminal block FA1-TE2SD40P

FA-CBL**FMH-FY

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH-FY

FA1-MM40P

FA-CBL**MMH

FA-CBL**FMH-FY

FA1-MM40P

FA-CBL**MMH

Input

NP1X3202-W

FA-TBS40P

NP1X6406-W
NP1Y32T09P1

Output

NP1Y32U09P1

Junction terminal block FA1-TE2SD40P
FA-TBS40P

NP1Y64T09P1
NP1Y64U09P1
NP1W3206T
NP1W3206U

I/O combined

Junction terminal block FA1-TE2SD40P
FA-TBS40P

NP1W6406T
NP1W6406U

63

9. EXTERNAL DIMENSIONS[Unit : mm](1) FA1-MM40P

8.9

8.9

35.5

35.5

75

75

(2) FA1-MM20P

32

17.6

17.6

41.5

41.5

32

64

10. PRECAUTIONS
For wiring to the terminal block, refer to the manual of the programmable controller module to be connected, published by
Mitsubishi Electric.

11. TROUBLESHOOTING
When the cable junction unit cannot be installed on the DIN rail.
When the cable junction unit cannot be removed from the DIN rail.
Check item
Is it the correct installation method?
Is it the correct removing method?

ActionCheck if the installation method is correct.
(5-2. Connecting method)
Check if the removing method is correct.
(5-2. Connecting method)

When the cable cannot be installed on the cable junction unit.
Check item
Is the connector oriented correctly?

ActionConnect the cable with the correct connector orientation.

If no signal is output.
Check item
Is there any looseness in the mounting of the connected?
Is the combination of connected devices correct?
Is there contact failure due to insulating foreign matter?

ActionMake sure the connector is securely attached.
Check if the combination of connected devices is correct.
(8. CONNETABLE MODULES)
Check if there are any problems with the wiring of theconnected device.

If unintended signal output or continuity
Check item
Is the combination of connected devices correct?
Is there contact failure due to insulating foreign matter?

ActionCheck if the combination of connected devices is correct.
(8. CONNETABLE MODULES)
Check if there are any problems with the wiring of theconnected device.

65

12. GRATIS WARRANTY TERMS AND GRATIS WARRANTY RANGE
If any fault or defect (hereinafter referred to as "Failure") attributable to Mitsubishi Electric Engineering should occur within
the gratis warranty period, Mitsubishi Electric Engineering shall replace the product free of charge via the distributor fromwhom you made your purchase.
● Gratis warranty period
The gratis warranty period of this product shall be one (1) year from the date of purchase or delivery to the designatedplace.
Note that the gratis warranty period shall be limited to 18 months after manufacturing, which includes six months as
the distribution period in the market.
In addition, the gratis warranty period of the product after repair is the same as that of the product before repair.
● Gratis warranty range(1) The gratis warranty range shall be limited to normal use based on the usage conditions, methods and environment,
etc., defined by the terms and precautions, etc., given in the instruction manual, user’s manual, and caution labels on
the product.
(2) In the following cases, a repair fee shall be applied even if within the gratis warranty period.
1) Failure resulting from inappropriate storage or handling, carelessness or negligence by the user, or Failure causedby the user's hardware or software design.
2) Failure caused by unapproved modifications, etc., to the product by the user.
3) Failure that could have been avoided if, when the Mitsubishi Electric Engineering product was assembled into theuser's device, safeguards defined by legal regulations applicable to the user's device or functions or structuresconsidered standard by the industry had been provided.
4) Failure recognized as preventable if the consumed products specified in instruction manuals, etc., were normally
maintained or replaced.
5) Replacement of consumable parts (relays, etc.).
6) Failure caused by external factors beyond anyone's control such as fires or abnormal voltage, and Failure caused
by Force Majeure such as earthquakes, lightning, or wind and water damage.
7) Failure caused by reasons unpredictable by scientific technology standards at the time of shipment from Mitsubishi
Electric Engineering.
8) Any other failure not attributable to Mitsubishi Electric Engineering or found by the user to not be attributable to
Mitsubishi Electric Engineering.

13. EXCLUSION FROM LIABILITY FOR OPPORTUNITY LOSS AND SECONDARY LOSS
Regardless of the gratis warranty period, Mitsubishi Electric Engineering shall not be liable for compensation for damages
arising from causes not attributable to Mitsubishi Electric Engineering, opportunity losses or lost profits incurred by theuser due to Failures of Mitsubishi Electric Engineering products, damages or secondary damages arising from special
circumstances, whether foreseen or unforeseen by Mitsubishi Electric Engineering, compensation for accidents,
compensation for damages to products other than Mitsubishi Electric Engineering products, or compensation for
replacement work, readjustment of onsite machinery and equipment, startup test runs or other duties carried out by theuser.

14. TRADEMARKSMELSEC iQ-R, MELSEC iQ-F, MELSEC, CC-Link IE Field, CC-Link IE and CC-Link are trademarks or registeredtrademarks of Mitsubishi Electric Corporation. Other company names and product names in the text are trademarks orregistered trademarks of each company.
In some cases, trademark symbols such as '™' or '®' are not specified in this manual.

66

FOR SAFE OPERATIONS● This product has been manufactured as a general-purpose part for general industries, and has
not been designed or manufactured to be incorporated in a device or system used in purposes
related to human life.
● Before using the product for special purposes such as nuclear power, electric power, aerospace,
medicine or passenger movement vehicles, consult with Mitsubishi Electric Engineering.
● This product has been manufactured under strict quality control. However, when installing the
product where major accidents or losses could occur if the product fails, install appropriate
backup or failsafe functions in the system.

67

NAGOYA ENGINEERING OFFICE

50D-FG0785(2403)MEE

1-9, Daiko-Minami, 1-Chome, Higashi-ku, Nagoya, Aichi 461-0047 Japan
Phone +81-52-6495 URL:https://www.mitsubishielectricengineering.com/

New publication, effective Mar. 2024.
Specifications subject to change without notice.