Careful design for silent operation
can realize the easy operation innight and early morning time.

Reliable design for a variety of safety
devices is realized, earthquake detector is equipped as standard device.
Various safety device, and fail safe in feedwater and combustion control is strengthening the safety further.
Earthquake detector is provided as standard device. When the Japanese (seismic)
scale is detected at a little under 5 seismic
intensity, boiler is stopped automatically,and secondary disaster can be prevented.

Low noise fan mounted or noise absorbing structure employed
are reducing the operation noise. Then you do not need to worry about complaining from neighborhood.

STOPAnyone
easy operation

Invertor gets electric power saving
Invertor is provided as standard equipment. Therefore the revolution of blower motor is properly controlled and the electric
consumption is reduced.

Necessary and
Auxiliary Equipment

Anyone can operate only topush start button !

ALLMODELS
EASY TOOPERATE

OptionBoiler is always kept in
the best condition

WATER SOFTENER
Provides the boiler withthe most suitable water after
treatment by our water softenerConcentrated Blow

SS series

Chemical Injection
Equipment

Controller operates concentrated blow automaticallydepending on operating conditions of the boiler.
Optimum timing of overall blow is informed by lampindication.
* EB-500N and EB-500PN include as a standard feature.

Saves Your Operation Work

Keeps boiler in good condition
for a longer period byChemical Injection

Automatic Overall Blow Control
CP-W series
CP- X series

Boiler Chemicals

Controller signal instructs overall blow automatically,
depending on operating conditions of the boiler.

Multi-Boilers
Control System

Multi-Functional Chemicals
for protection against
corrosion and scale sticking*We might be unable to export due
to the regulation of your country.
SAMCLEAN S-125
Please contact us for confirmation. Category Code : G6, G7
NSF Registration No. 166985

Multi-Boilers Control Panel can control multi-boilers
and maintain the best operating conditions.
Even if there is a sudden change in steam load andany trouble with boilers, it is possible to supply steam
constantly.

International Division (Osaka)
ADDRESSPMO EX Shin-Osaka 5th floor, 4−2−10 Miyahara,
Yodogawa-ku, Osaka, 532−0003 JapanTEL+81−6−6152−8135

FAX+81−6−6152−8128

E-MAILoverseas@samson.co.jp

WEB SITE

https://www.samson.co.jp/en/

SAMSOLUTION INTERNATIONAL CO., LTD.
ADDRESS

7F-8, NO.12, LN.609, SEC.5,CHONGXIN RD., SANCHONG DIST.,NEW TAIPEI CITY 24159, TAIWAN(R.O.C.)

T

E

L＋886-2-2278-3636

FAX＋886-2-2278-3535

WEB SITE

https://www.samson.co.jp/tw/

S AMSOLUTION B OILER SYSTEM

For a sustainable future of energy and foodEB Series

EB Series

Feature 1Unit

EB-160S

ON-OFF control drop the operation efficiency as the consumption of steam is reduced. In case of ECO BOY
employing 3-position control, it is continued to operate, even if the consumption of steam is reduced to ahalf. Consequently few number of ON-OFF control is operated and the operation Efficiency
efficiency is improved.
（％）

EB-250N

9690

EB-500N

EB-350N

Type of Boiler

EB-250PN

EB-350PN

Max. Pressure

MPa（kgf/cm²）

0.69
（7）

0.98
（10）

Working Pressure Range

MPa

0.39〜0.59

0.39〜0.88

1.19（12）When the comparison is made between the former ON-OFF control and New
EB-350N/PN employing 3-position control, you can find the following advantage inthe fuel cost and the environmental CO2 reduction.

1.58
（16）

Equivalent Evaporation

kg/h

160

250

350

500

250

350500Heat Output

kW（kcal）

100（86,200）

157（135,000）

219（189,000）

313（270,000）

157（135,000）

219（189,000）

313（270,000）

4.98

4.12

4.98

4.98

82

5266

82

Boiler Eﬃciency％

Heating Surface Area

ｍ²

3.1

4.12

4.98

Holding Water Volume

L40

52

66

90

85

Type of Burner
ON-OFF96

CO2Reduction

ON-OFFIgnition

AC Spark Ignition

Flame Detection
kg330

430

530655560

720

Weight in Operation

kg

370

485

600

740

620

790

945

13A

m³（N）
/h

9.9

15.4

21.6

32.7

14.5

20.3

29.0

LPG
Propane

m³（N）
/h

4.3

6.7

9.4

14.2

6.3

8.8

12.5

kg/h

8.6

13.5

18.9

28.6

12.7

17.7

25.3

LPG
Butane

m³（N）
/h

3.4

5.3

7.4

11.2

4.9

6.9

9.9

kg/h

8.8

13.7

19.2

29.1

12.9

18.0

25.7

13A

kPa
（mmAq）

LPG

Feature 2

2.8±0.5（280±50）

Available Electricity

kW

Normal Temperature:0.6
High Temperature:0.8

Total Electric Capacity

kVANormal Temperature:1.23 Normal Temperature:1.75 Normal Temperature:2.31 Normal Temperature:2.93 Normal Temperature:1.75 Normal Temperature:2.31 Normal Temperature:2.93
High Temperature:1.44
High Temperature:1.79
High Temperature:2.31
High Temperature:2.93
High Temperature:1.79
High Temperature:2.31
High Temperature:2.93

Main Wire Sizeｍｍ²

2

Power Breaker Capacity

A15

Normal Temperature:1.0
High Temperature:1.0

Normal Temperature:15A

Gas Inlet（13A）

Connection Dia.

Normal Temperature:1.35 Normal Temperature:1.70
High Temperature:1.35
High Temperature:1.70

High Temperature:20A

25A

20A

32A

Gas Inlet
（LPG）

40A

25A

Steam Outlet
Safety Valve Blow

32A

20A

Normal Temperature:1.0
High Temperature:1.0

25A

25A

●Equivalent Evaporation 350kg/h Boiler 1unit●Operating Time 1,500Hours/Years（6Hours 250days）●Average Load 50% ●Fuel Cost ¥90/㎥N（13A）

50100（％）
Load Factor

EB-350PN（With Economizer·3-Position Control）
EB-350N（Without Economizer·3-Position Control）
Conventional Equipment（Without Economizer·ON-OFF Control）

Boiler Efficiency

96 %

40A

25A

40A
32A

25A

High boiler efficiency establish high economical operationHigh boiler
efficiency establish
high economical
operationIn addition to energy saving operation by 3-position control, this become much more economical by reducing
fuel at higher efficiency of boiler.

20A

32A

25A
32A

Boiler Water Blow

Normal Temperature:1.35 Normal Temperature:1.70
High Temperature:1.35
High Temperature:1.70

Normal Temperature:15A High Temperature:20A

40A

25A

32A

EB-250PN
EB-350PN
EB-500PN

Boiler Efficiency

90 %EB-160S
EB-250N
EB-350N

25A

Feed Water Tank Overﬂow

20A

25A

20A

Economizer Drain

25A
25A

Air Inlet

10A

15A

Chemical Inlet

10A15A

φ150

φ250

Feature 315A

Chimneyｍｍ

φ120

φ150

φ200

φ250

1.The above speciﬁcations are based on the following standard values in Japan.
Steam pressure 0.49MPa(5kgf/cm2)
Feed water temp. 15℃35℃
Feed air temp.
Lower heating value 13A : 40.6 MJ/m3(N) {9,700 kcal/m3(N)}Propane : 93.7 MJ/m3(N) {22,380 kcal/m3(N)}, 46.4 MJ/kg {11,080 kcal/kg}
Butane: 118.9 MJ/m3(N) {28,400 kcal/m3(N)}, 45.7 MJ/kg {10,920 kcal/kg}

EB-160S

Item832912

8329121,845

1,934

1,995

1,934

1,995

Steam outlet

Steam outlet

It is easy to understand the operation condition of boiler by coloring on operation button, and simple tooperate by one button control.

Safety valve blow

Unit

831

905

1,258

1,497

1,952

1,952

OperatingCondition

Gas Inlet

Gas Inlet
Feed watertank overflow
Feed water
inlet

Feed watertank overflow
Feed water
inlet
Boilerwater blow

Easy tosee and control

Boiler condition notice by Operating Switch

Normal Temperature:675 Normal Temperature:715 Normal Temperature:789 Normal Temperature:915 Normal Temperature:989
High Temperature:718 High Temperature:748 High Temperature:832 High Temperature:955 High Temperature:1030

752

Clear design establishes easy control

Front panel is clear design of One-button Design

3. The following allowance is considered as unavoidable measurement error :Measurement error in boiler eﬃciency ±2%
Measurement error in combustion (input) ±3.5%
4. Speciﬁcations are subject to change without prior notice.
* 200-480V can be available by transformer.

2.Please always supply with gas at the stable pressure within standard range at anytime of boiler stop,boiler operation and other equipment operation.

Chimney

3.0t / Year Reduction
5.8t / Year Reduction

Efficiency is on a level with the best in the industry!
Boiler efficiency at rated operation is standardized as 90%
except EB-500N. Furthermore, the efficiency of Boilers with economizer
reach to high level as 96%.

*AC200V 3φ（50/60Hz）

Feed Water Inlet

Safety valve blow

¥120.000/Year Reduction¥230.000/ Year Reduction

850

2.0±0.5（200±50）

Power Supply

Unit

EB-350N
EB-350PN (With Economizer)

13~14%
UP

8~9%
UPFlame RodWeight

Item

EB-350N
EB-350PN (With Economizer)

Calculation Condition

3-Position（High-Low-OFF）Feed Water Control

Supply gaspressure

FuelReduction

BlastCombustion Control

FuelConsumption

Low Fuel Consumption & CO2 Reduction

EB-500PN

Once-Through Boiler

Hydraulic Testing Pressure MPa（kgf/cｍ²）

3-position control
establish savingenergyIn this capacity of boiler, we are the first manufacturer to provide
3-position control with all models. (Except for EB-160S)

EB-160S EB-250N EB-350N EB-500N
EB-250PN EB-350PN EB-500PN
Item

Energy saving operation by 3-position control

Overall Blow
NoticeInspection
NoticeError
NoticeChimney

Shape differences depend on the model or specification.
This drawing shows EB-500N

Shape differences depend on the model or specification.
This drawing shows EB-350N
Boiler water blow

12