New Sensor Network Technology
AnyWire for wiring savings

AnyWire Product Catalog

DigitalLinkSensor

Concept of AnyWireASLINK
AnyWire always focuses on “manufacturing from the viewpoint of on-site” and continues to send out various
proposals. AnyWireASLINK is the breakthrough Sho-Haisen system that offers additional value in diverse
ways in continuation to all of the advantages and features of the conventional AnyWire Sho-Haisen system.

Features and advantages of conventional Sho-Haisen
AnyWire Sho-Haisen
Free cable}

General-purpose electric wire
Already installed electric wire
Spare electric wireOK!

Transmissionby 2-core*See the “Features of AnyWire Sho-Haisen” on Page 2 for details.

Topology freeHigh noise
resistance
se

Noi

Power
Power supply
supply2-coreEasy connection andeasy branching

General Sho-Haisen
Wiring savings
Resource savings

24V
12V

SignalSignal0V

No influence ontransmission!

New＋- Insulation displacement
connector- For branching and extending- Same type for male andfemaleMan-hour savings
Space savings

Added Values

Achieved by “evolution” of I/O terminal

Achieved by “diagnosis” incorporating sensor
into Sho-Haisen

Innovatively diagnosing Sho-Haisen

Diagnosis
Diagnosis ofof sensor
sensorIncreased downsizing

Monitoring of sensing level

Disconnection detection ofconnected sensor cable

Setting of sensitivity andthreshold from higher controller＝

Completely new Sho-Haisen system

in which all elements are incorporated into one

That is “Innovatively diagnosing Sho-Haisen”
D i g i t a l

01

AnyWireASLINK Systeml i n ks e n s o r

iQSS compatible

e-F@ctory compatible

AnyWireASLINK is an iQSS-compatible application.

In addition, “visualization” and “diagnosis” from a terminal at a remote area to 1 bit at the

Seamlessly combines comprehensive applications such as a

end by linkage with e-F@ctory. New relationship between sequencer and sensor is realized.

sequencer and GOT, and sensor control.
Remote monitoring
Remote maintenance

Logistics center
・MELSEC sequencer

リモート
メンテナンス

Logistics
headquarters

ASLINKSENSOR
・GOTPrediction maintenance
Setup changeLine additional installation

Sensors are incorporated into FA integrated concept iQ Platform of
Mitsubishi Electric Corporation. Solutions realize customer TCO
reductions which continuously enhance the linkage between asensor, sequencer, displayer and engineering environment.
This is IQ Sensor Solution ().

Remote monitoring Remote maintenanceReadout of sensor sensitivity setting
Writing of sensor sensitivity setting* AnyWire is an
e-F@ctory alliance.

Setting
manufacturer
headquarters* See our “Energy monitoring energy saving support” catalog for details on power and current monitoring.

Features of AnyWire Sho-Haisen
Free cable (any transmission media (electric wire) can be selected)
Inexpensive general-purpose cabtire cables which are available from anywhere can be used. Even spare electric wires
and electric wires which have already been used in another system can be used as they are in the high noise resistance
AnyWireASLINK if they have electric wire diameters which are within the operating condition range. The link connector

General-purpose
cabtire cable(only for 4 poles) for a cabtire cable is also available.

(Note) Contact us separately for details on use.

Transmission by 2-core
2-corePowersupplySignalSince the AnyWireASLINK system employs a power supply superposition method, it can transmit power and signals in
2-core using a 2-wire type (non-insulation) type terminal. In addition, if current capacity on the load side is large, aterminal of a 4-wire (insulation) type which can locally supply power can also be selected by separately preparing a
power source. Furthermore, a system in which these two terminals are mixed can be built.

Topology free (No limitation in branching)T-branchMulti-drop

Star wiring

Tree wiring

AnyWireASLINK system allows for flexible branch and connection. There is no detailed
regulation such as designation of the branching method and minimum distance between therespective terminals, and various wiring methods such as T-branch, multi-drop, star and tree
wiring can be selected, and there is no problem even if these methods are mixed.
* It is recommended to wire with T-branch in order to easily isolate at time of trouble.
* It is recommended to decrease the number of branches wherever possible for stabletransmission (within 10).

High noise resistance
AnyWireASLINK system is① Different in transmission voltage: 24V DC compared to general 5V DC. Greater margin can be taken for noise.
② Different in transmission clock: 27kHz compared to general approx. 3 to 10Mbps. With a sufficiently large clock width, hardly susceptible to noise.

AnyWireGeneral communication
24V
e
Nois
5V
0V
0.3μs

24V

24V

12V

12V

12V

12V

0V

0V

0V

0V

1μs

24V

37μs

Communication error occurs!

e

Nois

24V

24V
12V
0V
1μs

No influence on transmission!

Easy connection and easy branching
Usability which conventional types do not have is achieved by using the
AnyWire link connector

Features of link-connector and how to use
You can sandwich wire in a sleeveeven in the middle or at the end of
an electric wire.

Clamp with a dedicated tool to crimp.
(See the accessory items.)

T-branch, 4-branch or extension isallowed.
Working time is significantly reduced.

- Branching can be made even in the middle of wiring because of crimping.
- No waste is produced because an electric wire is not cut/sheath is not stripped.
- There is no difference between male and female, and are the same models, so it
is easy to understand.

AnyWireASLINK System

02

Features of AnyWireASLINK
Innovatively diagnosing Sho-Haisen - “Increased downsizing”< Increase in space efficiency by downsizing of I/O terminal >Elimination of BOX is promoted by increased downsizing including small I/O terminal of fingertip size allowing
dispersion from 1-point and 2-point, and 8-point terminal of terminal block type realizing compact size of volume ratioof 1/3 in comparison with conventional types.

BeforeAfter

Replaceable type jig is used. Downsizing is attemptedby ingenuity of design, however, the relay box is bulky
and downsizing cannot be achieved as expected.
In order to respond to a wide variety of products,
freedom of design is also necessary, and it is desirable
to simultaneously save energy by downsizing and weightsavings.

ASLINK is a very small terminal comparable to a relay connector.
Since ASLINKER is directly installed to a cylinder, a relay box forsensor wiring can be removed, and downsizing and weight saving
can be realized.
Space for box is removed,and downsizing
can be achieved.

The input/output terminal ishoused in the relay box.

ASLINKER
Installed on a cylinder

Increase in freedomof design

Jig size reduced approx. 1/3,
light-weight

Recovery fromfailure is made easy.

Innovatively diagnosing Sho-Haisen - “Detection of disconnection of connected sensor cable”< Whether sensor non-detection? or disconnection? can immediately be determined >It was necessary for conventional I/O terminals to confirm whether sensor was in a non-detection state or whether
sensor itself was in failure (sensor cable disconnection) for actual product. However, remote monitoring is allowed fromhigher controller and disconnected sensor is also easily identified by mounting this function.

BeforeAfter

ID (address) which should turn ON at a determinedtiming is not turned ON and the equipment stops.

Disconnection detection function for sensor cable mounted on
ASLINKER can significantly reduce time spent on investigation of
cause. Monitoring is also facilitated by combination with GOT, anda highly visible monitoring system is allowed to be built.

- Is the sensor in failure?
- Is the mechanism part in failure?
- Is the terminal in failure?
- Is the wire disconnected?

Information notice!

There are various causes as to why the sensor is in
OFF status, and confirmation and inspection with
input which cannot be judged on the controller side
are essential. This means that an investigation into thecause will take many hours.

03

AnyWireASLINK System

No.0

ON

No.1

OFF

No.2

ON

No.3

OFF

Detection of connected sensor disconnection!

Input error?

Disconnection!

Error!
Position: Address 1
Type: ASLINKER
Status: I/O disconnection

No.0

ON

No.1

OFF

No.2

ON

No.3

ON

Decrease in time forinvestigation of cause

Reduction inmaintenance man-hours

Decrease in equipment stop time
→ Increase in availability

Diagnosis of sensor – “Monitoring of sensing level”＜ Diagnosing not only ON/OFF but also measured value for preventive maintenance ＞
Photoelectric sensor of ON/OFF operation etc., cannot actually determine ON far from OFF or ON close to OFF.
ASLINKSENSOR allowing diagnosing of measured values can monitor its state from a higher controller, therefore, it cangrasp the state of the sensor. Use of ASLINKMONITOR also allows for confirmation of measured values on-site.

BeforeAfter

The typical sensor judges ON and OFF on a
threshold boundary and outputs a signal.
Therefore, the typical sensor cannot detect adrop in actual sensing level etc., (such asdeviation of light axis and adherence of dirt) andsuddenly stops operation at the instant when thesensing level falls below the threshold.

ASLINKSENSOR always monitors sensing level of a sensor.
The sensing level is converted into digital data, which istransmitted to a higher controller and is monitored by GOT,
therefore, preventive measures such as replacement, adjustment
and cleaning can be taken before “the sensor can be turned ON.”
Image of sensing level drop
detection[Example of status which can be monitored]- Sensing level- Applicable ID (address)
Error!
- Sensor type
Position: Address 16
Type: Transmission sensor
Status: Level dropON
(Sufficient)Light receiving
amount dropON
(Caution)OFF(Insufficient)

InitialMonitor search isallowed in combination
with GOT.

After aging

Comprehension ofsensing level

System emergency stop
prevention

Monitor isalso allowed by GOT.

Diagnosis of sensor – “Setting of sensitivity and threshold from higher controller”＜ Collective change of sensitivity setting and reduction in adjustment production steps
and man-hours by fine adjustment of threshold ＞

Maximum value
ThresholdMinimum value

It was common to perform sensitivity setting of sensor and adjustment of threshold one by one on-site. However,
ASLINKSENSOR allows collective setting changes of all sensors to be operated from a higher position. ASLINKSENSOR
can also save set values. Therefore, it minimizes downtime such as at the time of setup change. In addition, this canprevent “momentary stop” before it happens during adjustment of threshold, and can control maintenance timing.

BeforeAfter

Sensitivity setting of each sensor and recordingof set values to ensure traceability are, in
general, manually performed even today.
Therefore, both setting and recording required alarge number of man-hours over many hours.

ASLINKAMP and ASLINKSENSOR allow the sensing level to be
adjusted from a higher controller and also allow current set values
to be saved. On the other hand, they also allow the saved set
values to be reflected onto each sensor, resulting in significant
reduction in man-hours. In addition, momentary stop can beprevented by adjustment of threshold to control maintenancetiming.

Setting

Automatic
setting

AutomaticrecordRecordReduction in adjustment
production steps and man-hours

Reduction in
set value recording operation

Batch/individual setting
are selectable.

AnyWireASLINK System

04

05

AnyWireASLINK System

INDEX
AnyWireASLINK System Catalog
Contents
Concept
・Concept of AnyWireASLINK・・・・・・01

・e-F@ctory and iQSS Compatible

・・・・・・02

・Features of AnyWire Sho-Haisen

・・・・・・02

・Features of AnyWireASLINK・・・・・・03

Technical Guide
・Product Configuration

・・・・・・07

・System Configuration

・・・・・・09

・Various Connection Methods

・・・・・・13

・Basic Transmission Specifications

・・・・・・14

・Functions of AnyWireASLINK System

・・・・・・15

・List of Functions and Features of Slave Units ・・・・・・16

Product Lineup
・Master Units/Terminator・・・・・・18

・Engineering Tool

・・・・・・24

・Accessories/Special Units

・・・・・・28

・Slave Units (I/O)

・・・・・・34

・Slave Units (Analog)

・・・・・・74

・Slave Units (Sensor/Amplifier)・・・・・・86

・Third Party

・・・・・ 156

Appendix
・Consumption Current Calculation
・・・・・ 161
(How to calculate number of connectable units)・Address Writer・・・・・ 163

・Correspondence Table of Applicable Connectors・・・・・ 165

AnyWireASLINK System

06

Product configuration of AnyWireASLINKMaster unit

ASLINKMASTER
Master unit compatible with a MELSEC sequencer and various widely prevalent industrial open networks
・Bridge unit for CC-LINK
network・Interface for each
MELSEC series
MELSEC iQ-R AnyWireASLINKMaster unit

MELSEC-L AnyWireASLINKMaster unit

MELSEC-Q AnyWireASLINKMaster unit

MELSEC iQ-F AnyWireASLINKMaster unit

MELSEC-F AnyWireASLINKMaster block

CC-LinkーAnyWireASLINK CC-Link IE FieldーAnyWireASLINK
Bridge unit
Bridge unit

I/O terminal
ASLINKER[ Circuit block diagram ]General-purpose input/output
equipment ready unit

ASLINKTERMINAL
General-purpose input/output
equipment ready terminal

LINK
circuitSensor head
(Detecting part)

LINK
circuitOutput I/F

Small 8-point
terminal

Sensor amplifier(Amplifying part)

LINK
circuit

Input I/F

Connection terminal(I/O connection part)

LINK 回路

出力 I/F

Connection terminal(I/O connection part)

LINK
circuit

Small terminal
block terminal

Sensor amplifier(Amplifying part)

Input I/F

Sensor head
(Detecting part)

Equipment
負荷側機器
onload side
負荷側機器
負荷側機器
負荷側機器
負荷側機器
負荷側機器
負荷側機器

Sensor head
(Detecting part)

Small terminal
block terminal

LINK
circuitOutput I/F

Equipment
負荷側機器
onload side
負荷側機器
負荷側機器
負荷側機器
負荷側機器
負荷側機器
負荷側機器

Analog terminal
ASLINKAMP
Analog input/output unit

[ Circuit block diagram ]LINK circuit

Analoginput unit

Input I/F

(A/D conversion part)AD output equipment

LINK circuit

Analogoutput unit

Sensor/Amplifier
ASLINKSENSOR[ Circuit block diagram ]Circuit block diagram

Digital link function built-in sensor

ASLINKAMP
Multi-amplifier and analog input
unit compatible with commercial
sensor head

Circuit block diagram

Optional address sensing level display unit

AnyWireASLINK System

LINK
circuit

Input I/F
(A/D conversion part)

Sensor amplifier(Amplifying part)

Sensor head
(Detecting part)[ Circuit block diagram ]ASLINKMONITOR

07

Equipment
on load side

[ Circuit block diagram ]Small 8-point
terminal

Slave unit

Sensor amplifier(Amplifying part)

Input I/F

LINK
circuit

Input I/F
(A/D conversion part)

Sensor amplifier(Amplifying part)

Sensor head (light emitting part)
Sensor head (light receiving part)

Output I/F(D/A conversion part)

DA input equipment

・Interface for
PC Bus・Gateway foropen network
AnyWireASLINKDeviceNet Gateway

AnyWireASLINKPROFIBUS Gateway

Master I/F
for PCI Express

AnyWireASLINKEthernet Gateway

・Resend unit

・Bridge for
AnyWire DB A20

Resend unit

Bridge for
AnyWire DB A20MODE

ASLINK Bridge

AB27-AL
Resend Unit

BR27-01[ Example of product ]

O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

SET

RDY LINK

LINK SET ALM

FG 24V 0V D G

DP DN

FG 24V 0V

DP DN

D

G

24V
drop

P.19

ID (address)
Duplicate/
Not set* With limitation

Cable type

P.35

M12 connector type[ Example of product ]

O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setSmall terminal
block terminal

Small 8-point
terminal[ Example of product ]

P.49

O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setP.75

Analog input unit

[ Example of product ]

O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value■ Common■ Laser■ Photoelectric

O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not set* With limitation■ Photo interrupter
Proximity type

Photoelectric
type

Pressure
type

Cylinder type

O
N
O
F
F

Hi
LO
NG

[ Example of product ]Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

Maximum value
Threshold

Extension unit
(additionally combined)

Minimum value■ Proximity, Cylinder, pressure
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
ThresholdP.87

unnecessary

Minimum value

Interference
countermeasureunnecessary

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setBase unit

P.105

For fiber head

[ Example of product ]

O
N
O
F
F

Small display unit

Line monitor

Hi
LO
NG

Maximum value
ThresholdMinimum value

Interference
countermeasureunnecessary

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setP.152*Check details of each product with the product pages or the operation manual.

AnyWireASLINK System

08

System configuration◆ System consisting of 2-wire type only (when local power supply is unnecessary)
Master unit

For MELSEC iQ-R

For CC-Link

For MELSEC-L

For MELSEC-Q

For CC-Link IE Field For DeviceNet

For MELSEC iQ-F

For MELSEC-F

For PROFIBUS

For Ethernet

ASLINKER (M12 connector type)

ASLINKER (Cable type)
Generalpurpose
sensor

Generalpurpose
outputequipment

For PCI Express

Generalpurpose
sensor

Generalpurpose
outputequipment

M12 generalpurpose
output sensor

M12 generalpurpose
sensorAddress writer

24V DC
2-wire type

See page 25 and 163 fordetails on the address
writer.

2-wire type2-wire type

ASLINKAMP→ Commerciallyavailable head

(fiber, special input/
output)2-pole LP connector→ Coupling◇Line color of dedicated flat cable and connector pin No.
Dedicated flat
Pin No. of LP
cable size
connector
Transmission
0.75mm2 1.25mm2 (link connector)
line

2-core

DN
DP

Black

Black

Red

White spiralon red1
2

Dedicated flat
cable (2-core)
2-wire type

ASLINKSENSOR

Reflecting object

Photoelectricrecurrent
reflection type

Photoelectrictransmission type

M12

M18

Reflection
plate

Photoelectric spreadreflection type

AnyWireASLINK
small display unit

Cylinder type(cylinder is not
attached)

Proximity type
Photo interrupter typePressuretype

Terminator(Waveform shaping module)[System configuration]
・There is a master interface for MELSEC iQ-R, L, Q, iQ-F which operates as an intelligent unit.
In addition, there is also a master block for MELSEC-F which operates as a specially added block.
There is a bridge for CC-Link and a bridge for CC-Link IE Field in addition to the above.
・There is a gateway for DeviceNet and a gateway for PROFIBUS as a master unit for open field bus, and there is also a
gateway for Ethernet compatibility with some Ethernet-linked protocols.
・Master interface for PCI Express is also available as a master unit for PC bus.
・ASLINKMASTER is incompatible with our “DB A40/A20 series” and “Bitty series” for connection.
・Connect a terminator (waveform shaping module) at the most distal end of the transmission line laid fromASLINKMASTER.
・Perform address setting of the terminal and initial setting of the sensor sensitivity by using an address writer.
(Sensor sensitivity setting is allowed from both of the address writer and higher controller.)

09

AnyWireASLINK System

◆ System in which 2-wire type and 4-wire type are mixed (when local power supply is unnecessary)
Master unit

For MELSEC iQ-R

For CC-Link

For MELSEC-L

For CC-Link IE Field For DeviceNet

For MELSEC iQ-F

For MELSEC-F

For PROFIBUS

For Ethernet

For PCI Express* When connecting to the external load for which power of the other system is separated
from AnyWireASLINK, make sure to use a terminal of the 4-wire (insulation) type.

2-core24V DCFor MELSEC-Q

24V DCASLINKER (Cable type)

ASLINKAMP

Generalpurpose
outputequipment

Generalpurpose
sensor

General- Generalpurpose purpose
outputsensor equipment

Only DP/DN isconnected

3

ASLINK filter◇Line color of dedicated flat cable and connector pin No.

ASLINKAMP

Dedicated flat
Pin No. of LP
cable size
connector
Transmission
0.75mm2 1.25mm2 (link connector)
line

4-core

Black
Red

White

White

Green

Brown

Generalpurpose
outputequipment

2-wire type4-wire type

Red

Generalpurpose
outputequipment

Only 2-wire type
is connected

Contact us for details
of ANF-01.

Black

Generalpurpose
sensorUsed for one amplifier(Base unit only)

ANF-01

DN
DP
0V
24V

ASLINKER (Cable type)

Commerciallyavailable head
(fiber, special input/output)

4

Local power supply

1
2
3
4

ASLINKER (Cable type)

Used forsome amplifiers(Base unit +extension unit)

Only 2-wire type is connected

4-pole LP connector

4-wire type
ASLINKER (M12 connector type)

M12 generalpurpose
sensorCommerciallyavailable head
(fiber, special
input/output)

2-wire type4-wire type

M12 generalpurpose
output sensor

Small terminal block terminal

ASLINKTERMINAL

2-wire type

Only 2-wire type is connected

4-wire type
General-purpose
sensor, etc.

Connection cable
Small 8-point terminal

Standard terminal block

Connection terminal (e-CON)
General-purpose
汎用センサ等
sensor,etc.

ASLINKSENSOR

Address writer
See page 25 and 163 fordetails on the address
writer.

General-purpose
sensor, etc.
Spring terminal block

Photoelectrictransmission type

General-purpose
sensor, etc.

Reflection
plateEuro terminal block

Photoelectric recurrent
reflection type2-wire type
M12

M18

Cylinder type(cylinder is not attached)
Reflecting
objectPhoto interrupter type

Only 2-wire type
is connected
Proximity
type

Pressuretype

Photoelectric spreadreflection type

AnyWireASLINK
small display unit

Terminator(Waveform shaping module)[System configuration]*Pay attention to the following item in addition to the content of [System configuration] on page 09.

・When you intend to expand the power supply capacity of AnyWireASLINK, use a terminal of the [4-wire (insulation) type] whichallows for local power supply.

AnyWireASLINK System

10System configuration◆ System for environment-resistant area

Ultracompact I/O terminal

Master unit

ASLINKER
For MELSEC iQ-R

For CC-Link

IP67

The main body of the IP67-capable remote
I/O is of 17mm × 38mm ultracompact size,
which is offered as three types: two-point
input/two-point output/one-point input,
one-point output. With no need to prepare

For MELSEC-L

For CC-Link IE Fielda waterproof box, polydispersion with asmall number of points in a watery envi-

IP67

ronment is realized at low cost. For the
I/O side cable end, an M12 connector or M8
connector can be selected for installation.
For MELSEC-Q

For DeviceNet
IP67

For MELSEC iQ-F

For PROFIBUS

For MELSEC-F

For Ethernet

For PCI Express

IP67

Due to the lineup of the “environment-resistant productseries,” polydispersion with a small number of points and
Sho-Haisen are easily realized even under harsh sites
requiring environment resistance such as car manufacturing lines, semiconductor manufacturing equipment, and food and beverage production lines. Moreover, low-cost diagnosis by using Sho-Haisen
direct-coupled sensors is also possible.

11

AnyWireASLINK System*As a Y-branch (2-branch) adapter, use OMRON type XS54-D426-5.
For branch line extension, the OMRON XS5 series can be connected.
The above should be purchased from distributors of OMRON products.

IP67

General-purpose sensor*For protecting the M12 connector(socket side), use OMRON waterproof
cover: type XS5Z-11.
(Plug side waterproof cover: type XS2Z-11)

Existing photoelectric, proximity, and various
other general-purpose sensors can be used asthey are.
Use of ultracompact remote I/O “ASLINKER”
enables Sho-Haisen or networking of sensors without changing brackets or methods of installation.

Sho-Haisen direct-coupled type

IP67

*For protecting the M12 connector (socket side),use OMRON waterproof cover: type XS5Z-11.
(Plug side waterproof cover: type XS2Z-11)

Diagnosis of Sensor

Photoelectric type with
M12 Smartclick connector

IP67

Since no remote I/O is made, “time and effort
required for connection between a remote I/O andsensors” can be completely eliminated, and wiring
can be minimized.

Proximity type with
M12 Smartclick connector

IP66

Fiber amplifier with
M12 Smartclickconnector

There are various cables & connection options for “environment-resistant product series.”
Wiring and branching work while securing environment resistance can be performed with a
1.25sq × 4-core cable (3/5/10m) with an M12 connector cable, which can be used as a trunk,a 4/8 branch unit, which enables simple branching, and so on. Also, for all the M12 connectors of these products, the Smartclick method excelling in workability is adopted.

OMRON XS5 series
IP67*For a trunk, use AnyWire’ s waterproof cable with an M12 connector.

*

is a registered trademark of OMRON Corporation.

AnyWireASLINK System

12Various Connection Methods◆ Connection of terminal side
There are roughly two types of methods for connection of terminals on AnyWireASLINK.
One method is the “2-wire (non-insulation) type” and the other method is the “4-wire (insulation) type.” For basic configuration of
AnyWireASLINK, connection with the 2-wire (non-insulation) type is assumed. Not only the transmission signal but also power tooperate the terminal and equipment on the load side are superimposed on these 2 electric wires.
A 4-wire (insulation) type is a terminal used when the current capacity on the load side is not covered by supply current of a 2-wire(non-insulation) type, and responds to both power supply from the master side and power supply on the local side. See page161 for how to calculate supply current on the terminal of each type.
Furthermore, when connecting to external load for which power of the other system separated from AnyWireASLINK is used, makesure to use a terminal of a 4-wire (insulation) type.

2-wire (non-insulation) type4-wire (insulation) type

・Number of wirings is decreased.
・This type can be used with power supplied only to themaster side.
・This type can be used for load of the closed circuit such asa sensor and LED.
・Power of maximum 2A is supplied to the local throughtransmission line.

・Load with large consumption current can be used.
・Common can be taken with power other than AnyWireASLINK.

■Power supply by powersuperimposition■Power supply to the entire system

Operation isavailable as it is
without anotherpower supply!

LJ51AW12BY
RUN LINK SET ALM

POWER

INPUT
100-200VAC

SET

AnyWireMAX 2A

LJ51AW12BY
RUN LINK SET ALM

POWER

INPUT
100-200VAC

Operation is alsoavailable evenwhen current capacity
on the load sideis larger!
24V DC power

SET

24V DC
AnyWireInput/
outputControl

2-wire linker

Input/
outputControlLoad

2-core cable on whichtransmission signal andpower are superimposed

2-wire linker

2-core cable on whichtransmission signal andpower are superimposed

4-wire linker

Power supply
for load

MAX 2A

24V DC

Load
Load
Load
Load

4-wire linker■Local power supply

2-wire sensor

LJ51AW12BY
RUN LINK SET ALM

POWER

2-wire sensor

INPUT
100-200VAC

SET

AnyWire2-wire amplifier

Head

MAX 2A

24V DC

24V DC power

2-wire amplifier

24V DC
Input/
outputControl

4-wire linker

Power supply
for load

Input/
outputControl2-core cable on whichtransmission signal andpower are superimposed

4-wire linker

Load
Load
Load
Load

◆ List of connection method classification for every terminal (slave equipment) type
ASLINKER
Type

Cable type M12 connector type

ASLINKTERMINALASLINKAMP
Fiber

Analog input
unit

Analog output
unit

ASLINKSENSOR

2-wire (non-insulation) type

○*1

○

×

○ *2

○

×

○

4-wire (insulation) type

○*

×

○

○*2

×

○

×

1

*1 ASLINKER of IP67 structure is also included.
* 2 Without 7 segment display/IP65 is 2-wire type (non-insulation), and with 7 segment display is 4-wire type (insulation).

13

AnyWireASLINK System

Basic transmission specifications◆ General specifications
Ambient temperature use

0 to 55℃

Ambient temperature storage-25℃ to 75℃

Ambient humidity use
Ambient humidity storage*This description is a representative general specification. Since some products have partially different
specifications, please check the instruction manual for details.

10 to 90%RH, No condensation

Atmosphere use

No corrosive gas

Altitude use *1

0 to 2000m

Pollution level *22 or less*1 Do not use or store the AnyWireASLINK equipment in an environment pressurized above the atmospheric pressure at altitude 0m. Malfunction may result.
*2 This is an index showing the degree of generation of conducting substance in an environment where the equipment is used. Pollution level 2 means generation of
non-conducting pollution only. However, temporary conduction may occur by accidental condensation in this environment.

◆ Performance specifications
Transmission clock
Transmission distance/
supply current

27kHz (37μs)
Size
1.25mm2

0.75mm2

0.5mm2

Transmission distanceDP-DN allowable supply current

50m or less2A or lessExceeding 50m, 100m or less

1A or lessExceeding 100m, 200m or less

0.5A or less

50m or less

1.2A or lessExceeding 50m, 100m or less

0.6A or lessExceeding 100m, 200m or less

0.3A or less

50m or less

0.8A or lessExceeding 50m, 100m or less

0.4A or lessExceeding 100m, 200m or less

0.2A or lessNumber of connection points

Up to 128 units (See page 161 and the following pages for the calculation method of the number of connectable units.)

Transmission method

DC power supply superimposed total frame/cyclic method

Connection mode

T-branch method, multi-drop method, star wiring method, tree branch method

Transmission protocol

AnyWireASLINK protocol

Error control

Double check, checksum
Up to 512 points (Input 256 points/output 256 points)
However, up to 128 points for FX3U-128ASL-M (Input + output ≦128 points) (number of input points is prioritizedin case of input + output ≧128 points)
Up to 384 points for FX5-ASL-M (Input + output ≦384 points) (Input up to 256 points/output up to 256 points)

Number of connection I/O points
RAS function
Electric wire used

Transmission line disconnection detection function, transmission line short-circuit detection function,transmission circuit drive power drop detection function ID (address) redundant/non-setting detection function
・General-purpose 2-wire/4-wire cable (VCTF, VCT 0.75 to 1.25mm2, rated temperature 70ºC)
・General-purpose electric wire (0.75 to 1.25mm2, rated temperature 70ºC)
・Dedicated flat cable (0.75 mm2/1.25mm2, rated temperature 90ºC)*3 ・Total length also includes the cable section of the terminal with cable.
・Size of the cable section of the terminal with cable is not included in this condition.
・When consumption current above DP-DN allowable supply current is required, use 4-wire terminal which allows for local power supply.
・When 2-wire type and 4-wire type are mixed, there is no problem if the current value obtained by adding current on the load side of the 2-wire type section
and operation current on all terminals of the 2-wire type and 4-wire type is within DP-DN allowable supply current.

◆ Transmission cycle time
Transmission I/O point number
setting
1 transmission cycle time

64 points
128 points
256 points
512 points(Input 32 points, output 32 points) (Input 64 points, output 64 points) (Input 128 points, output 128 points) (Input 256 points, output 256 points)
2.4ms

3.6ms

6.0ms

10.7msTransmission cycle time is time to update input and output data of the master unit and all slave units.
In actuality, “transmission delay time,” twice of transmission cycle time is generated by influence of the double check function.

◆ Precautions on transmission◇ If the transmission line is a 4-core line (DP, DN, 24V and 0V run together) and the length exceeds 50m, connect “ASLINK filter [model ANF-01]” inseries to 24V and 0V at a position where 4-core running starts together (immediately below the master unit in general connection state). (Maximum
allowable current 5A/DC24V)→ Signal is stabilized in order to enhance noise resistance and suppress influence of cross-talk by transmission signal.
→ In both cases when collectively supplying from the power source for master and when supplying from local power source, these shall be inserted.
→ When complying with CE standard, insert “ASLINK filter [model ANF-01]” regardless of laying method and distance.

*Master unit = ASLINKMASTER, slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKAMP, ASLINKSENSOR)

AnyWireASLINK System

14

Function of AnyWireASLINK system
AnyWireASLINK is a “Digital link sensor” having various functions.
Close combination of a higher controller and terminal contributes to “enhancement of availability” and“reduction in man-hours,” and smallness of terminal realizes “space saving.”
For various functions of AnyWireASLINK, parameters can be written and confirmed using the address writer(such as ARW-04). For more information, see page 163 or the operation manual (Product Guide) of eachproduct.

ARW-04

Digital link function “Digital link function” is a general term for characteristic functions which each product of AnyWireASLINK has.
O
N
O
F
F

Hi
LO
NG

Maximum value
ThresholdMinimum value*Digital link function to be mounted depends on products.

Sensing level monitoring

If a sensor and reflection plate are contaminated with dust or powdered dust when a photoelectric sensor
is used, sensitivity of detection is deteriorated and the operation becomes unstable or becomes disabled.
ASLINKAMP and ASLINKSENSOR can monitor not only ON/OFF of the sensor but also the sensing level
itself, that can realize preventive maintenance to prevent “momentary stop” before it happens.

Light receiving
amount drop

Read-out/writing of sensor sensitivity setting
Setting of boundary value (threshold) where a sensor turns ON/OFF and sensor sensitivity can beread out/written from a higher controller.
◇ The sensor the sensitivity of which drops is kept in operation until maintenance.
◇ Sensitivity adjustment is automatized at time of work setup change, etc., by recording
sensitivity setting in various cases.

Sensor cable disconnection detection

ThresholdSets threshold of ON/OFF detection.

Information notice!

When the sensor signal is turned OFF, whether “the sensor is turned OFF” or“power source is turned off and sensor is OFF” cannot be generally judged. Thisfunction can detect disconnection of a sensor, therefore, takes no time forinvestigation of cause.

Error!

Position: Address 1
Type: ASLINKER
Status: I/O disconnection

No.0

ON

No.1

OFF

No.2

ON

No.3

OFF

Detects disconnection of connected sensor!

Interference
countermeasureunnecessaryCountermeasure for interference of photoelectric sensor is unnecessary.
Since ASLINKAMP and ASLINKSENSOR operate in time division, nointerference occurs even when some sensors are simultaneously installed, anda shielding plate for interference countermeasure which has conventionallybeen required is unnecessary.

RAS function

Shielding plate is unnecessary.

Light emitting side Light receiving side

“RAS” function is a function that improves reliability, availability and serviceability.
* The transmission line consists of DP (data line, plus side) and DN (data line, minus side)(In case of 4-wire type, 24V line and 0V line are added to the above line.)

DP/DN
disconnection

Transmission line disconnection detection

DP/DN
shortcircuit

Transmission line short-circuit detection

24V
drop

ID (address)
Duplicate/
Not set15

When the transmission line (DP/DN line) is disconnected, the master detects this and notifies an error, and at thesame time, flashes the ASLINKMASTER indication lamp.
In addition, disconnection location of the transmission line can be searched from the separated address number.

When the transmission line (DP/DN line) is short-circuited, the master detects this and immediately stops
transmission, and notifies an error, and at the same time, flashes the ASLINKMASTER indication lamp.
Short-circuit can be quickly recognized and damage to equipment from trouble is prevented.

Transmission circuit drive power supply drop detection
When voltage of 24V DC power supplied to ASLINKMASTER drops, the master detects this and stops
transmission, and notifies an error, and at the same time, flashes the ASLINKMASTER indication lamp.
Voltage drop of transmission power can be quickly recognized and transmission trouble is prevented.

Disconnection!

Metal piece(such as chip and cable)

AnyWireASLINK master unit

Sequencer
24V DC voltage drops!

ID (address) duplex, non-setting detection
ASLINKMASTER recognizes ID (address) set to the connected digital link unit and digital link sensor, andnotifies errors if there is any duplex or unset unit or sensor.
In addition, error is also indicated with the associated terminal.

AnyWireASLINK System

ID (address)
Duplex setting!

List of Functions and Features of Slave Units○: Mounted

×: Not mounted /: Not applicable - : Not determined

Functions
Slave

Application

Sensing levelmonitoring

Transmission line disconnection detection,
Sensor sensitivity Sensor cable Interferenceline short-circuit detection,
setting
disconnection countermeasure Downsizing RAS transmission
transmission circuit drive power drop detection,
Read/write
unnecessary
detectionID(address) redundant, non-setting detection

Features

ASLINKER

General-purpose
sensor
General-purpose
output equipment

×

×

○

×

○

○

Sensor cable disconnection
detection,
without relay Box

ASLINKER(Cable type) *1

General-purpose
sensor
General-purpose
output equipment

×

×

○ *2

×

○

○

Sensor cable disconnection
detection, *2
without relay Box

ASLINKER

M12 connector
connection
Sensor

×

×

○ *2

×

○

○

Sensor cable disconnection
detection, *2
without relay Box

ASLINKTERMINAL

General-purpose
sensor
General-purpose
output equipment

×

×

×

×

○

○

Without relay Box

ASLINKTERMINAL

General-purpose
sensor
General-purpose
output equipment

×

×

×

×

○

○

Without relay Box

ASLINKTERMINAL

General-purpose
sensor
General-purpose
output equipment

×

×

×

×

○

○

Without relay Box

General-purpose
sensor
General-purpose
output equipment

×

×

×

×

○

○

Without relay Box

General-purpose
sensor
General-purpose
output equipment

×

×

×

×

○

○

Without relay Box

Dedicated fiber
head
General-purpose
fiber head

○

○

○

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box○○

Traceability,
without relay Box（Smart Linker）(M12 connector type)(Small terminal block terminal)(Integrated small terminal)(Small 8-point terminal)

ASLINKTERMINAL(Manifold driver)

DC
DC

X02SN

OUT

INPUT:5-

－

DC

5

IN

4
－

JAPAN

INPUT＋

1

3
＋

MADE

LOAD View

Bottom

－

OUT
DC

5

IN

4
－

X02SN

JAPAN

INPUT＋

1

3
＋

－

OUT
DC

5

IN

4
－

JAPAN

INPUT ＋

1

MADE

LOAD View

DC

Bottom

＋

IN
JAPAN

OUT
DC

OUT
DC

IN

OUT
DC

－

3

＋

OUT
DC
DC

3

X02SN
－

OUT

5

IN

－

3
＋

LOAD View

Bottom12214E6

JAPAN

4

INPUT＋

1

MADE

LOAD View

Bottom12214E6－INPUT:5-

JAPAN

4

24VDC
LOAD:2A5-48V

IN

G3R-OD－

5

INPUT ＋

1

MADE

＋

DC

LOAD View

X02SN

Bottom12214E6

JAPAN

4

INPUT:5-

24VDC
LOAD:2A5-48V－

5

G3R-OD

INPUT＋

1

MADE＋

12214E6

3

DC

LOAD View

X02SN

Bottom12214E6

－

JAPAN

4

INPUT:5-

0414C

0414C

12214E6

3

LOAD View

BottomIN

24VDC
LOAD:2A5-48V－

5

G3R-OD

INPUT＋

1＋

MADE

12214E612214E6

0414C

MADE

DC

3

DC

LOAD View

Bottom

X02SN

－

0414C

24VDC
LOAD:2A5-48V

INPUT:5-

24VDC
LOAD:2A5-48V

4

INPUT:5-

0414C
2

－

5

24VDC
LOAD:2A5-48V

G3R-OD

INPUT ＋

1

1

0

MADE

0414C
5

4

G3R-OD

DC(Fiber type)

X02SN

ASLINKAMPINPUT:5-

3

24VDC
LOAD:2A5-48V

0414C

G3R-ODALM

INPUT:5-

LINK

G3R-OD 24VDC
LOAD:2A5-48V

R/W

X02SN

(Relay terminal)

G3R-ODASLINKTERMINAL

0414C(Analog input/output unit)

Current/voltage
output/input
equipment

ASLINKSENSOR

Light detection

○

○

○

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box

ASLINKSENSOR

Light detection

○

○

○ *2

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box

ASLINKSENSOR

Magnetic
induction
detection

○

○

×

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box

ASLINKSENSOR

Cylinder rod
Position
detection

○

○

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box

Lighttransmission
detection

○

×

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box

Air pressure
detection

○

○

○

○

Preventive maintenance,
decrease in adjustment
production steps and man-hours,
traceability,
without relay Box

ASLINKAMP(Photoelectric type)（Laser type）(Proximity type)(Cylinder type)

ASLINKSENSOR(Photo interrupter type)

ASLINKSENSOR(Pressure type)*1 ASLINKER of IP67 structure is also included.
*2 With limitation

AnyWireASLINK System

16

17

AnyWireASLINK System

Master units /Terminator

Basic products necessary for configuration of AnyWireASLINK system.
Interface for Each MELSEC Series

・・・・・・19

Bridge Unit for CC-LINK Network

・・・・・・20

Gateway for Open Network

・・・・・・21

Interface for PC Bus・・・・・・21

Resend Unit

・・・・・・21

Bridge for AnyWire DB A20・・・・・・22

Terminator・・・・・・22

18

Master units /Terminator

ASLINKMASTER*For common function specifications, see page 14.

◆ Interface for Each MELSEC Series
・MELSEC iQ-R AnyWire Master unit
Model

RJ51AW12AL

Corresponding
CPU*1

R04CPU,

R120CPU,

R32ENCPU,

R32PCPU,

R32SFCPU-SET,

R08CPU,

R04ENCPU,

R120ENCPU,

R120PCPU,

R120SFCPU-SET,

R16CPU,

R08ENCPU,

R08PCPU,

R08SFCPU-SET,

R12CCPU-V,

R32CPU,

R16ENCPU,

R16PCPU,

R16SFCPU-SETPower supply

Standard price (¥)

Circuit: (supplied from iQ-R bus side)

Voltage +5[V]±5% Current 0.2[A] max.

Transmission line driver:(Supplied to front panel terminal)

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)Interface

Number of occupied
input/output points

32 points (I/O allotment: Interior 32 points)

Bridge Unit

Outer dimensions (mm)106.0(H)×27.8(W)×124(D)GatewayInterface for PC
Resend Unit
Bridge for
AnyWire DB A20
Terminator

Sold by Mitsubishi Electric Corporation

Mass

200g

Standard price (¥)

Sold by Mitsubishi Electric Corporation

・MELSEC-L AnyWireASLINK Master unitModel

LJ51AW12AL

Corresponding
CPU*1

L02SCPU, L02SCPU-P, L02CPU, L02CPU-P, L06CPU, L06CPU-P, L26CPU, L26CPU-P,
L26CPU-BT, L26CPU-PBT, LJ72GF15-T2

Power supply

Circuit: (supplied from L bus side)

Voltage +5[V]±5% Current 0.2[A] max.

Transmission line driver:(Supplied to front panel terminal)

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)

Number of occupied
input/output points

32 points (I/O allotment: Interior 32 points)

Outer dimensions (mm) 90.0(H) × 28.5(W) × 104.5(D)

Mass

200g

Standard price (¥)

Sold by Mitsubishi Electric Corporation

・MELSEC-Q AnyWireASLINK Master unit
Model

QJ51AW12AL

Corresponding
CPU*1

Q00JCPU,

Q02PHCPU,Q01UCPU,

Q26UDHCPU,

Q50UDEHCPU,

Q00CPU,

Q06PHCPU,Q02UCPU,

Q03UDECPU,

Q100UDEHCPU, Q06CCPU-V-B,

Q01CPU,

Q12PHCPU,

Q03UDCPU,

Q04UDEHCPU,

Q03UDVCPU,

Q12DCCPU-V,

Q02CPU,

Q25PHCPU,

Q04UDHCPU,

Q06UDEHCPU,

Q04UDVCPU,

Q24DHCCPU-V,

Q02HCPU,

Q12PRHCPU,

Q06UDHCPU,

Q10UDEHCPU,

Q06UDVCPU,

Q06HCPU,

Q25PRHCPU,

Q10UDHCPU,

Q13UDEHCPU,

Q13UDVCPU,

Q12HCPU,Q00UJCPU,

Q13UDHCPU,

Q20UDEHCPU,

Q26UDVCPU,

Q25HCPU,

Q00UCPU,

Q20UDHCPU,

Q26UDEHCPU,

Q06CCPU-V-H01

Power supply

Q06CCPU-V,

Circuit: (supplied from Q bus side)

Voltage +5[V]±5% Current 0.2[A] max.

Transmission line driver:(Supplied to front panel terminal)

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)

Number of occupied
input/output points

32 points (I/O allotment: Interior 32 points)

Outer dimensions (mm)98.0(H) × 27.4(W) × 100.0(D)

Mass

200g

Standard price (¥)

Sold by Mitsubishi Electric Corporation

・MELSEC iQ-F AnyWireASLINK Master unit
Model

FX5-ASL-M

Corresponding
CPU*1

FX5U, FX5UC

Power supply

Circuit: (Supplied from additionallyinstalled cable side)

Voltage +5[V] Current 0.13[A] max.

Transmission line driver:(Supplied to front panel terminal)

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)

Number of occupied
input/output points

8 points

Outer dimensions (mm)90.0(H) × 40.0(W) × 97.3(D)

Mass

200g

Standard price (¥)

Sold by Mitsubishi Electric Corporation

・MELSEC-F AnyWireASLINK Master block
Model

FX3U-128ASL-M

Corresponding
CPU*1

FX3G (Ver.1.00～）, FX3U (Ver.2.20～）, FX3GC (Ver.1.40～）, FX3UC (Ver.2.20～）

Power supply

Circuit: (Supplied from additionallyinstalled cable side)

Voltage +5[V] Current 0.13[A] max.

Transmission line driver:(Supplied to front panel terminal)

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)

Number of occupied
input/output points

8 points

Outer dimensions (mm)90.0(H) × 43.0(W) × 95.5(D)

Mass

200g

*1 Confirm details on corresponding CPU and other limitations with the AnyWireASLINK master unit users manual of each product published by Mitsubishi Electric Corporation.

*Master unit = ASLINKMASTER, slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKAMP, ASLINKSENSOR)

19

AnyWireASLINK System

*For common function specifications, see page 14.

◆ Bridge Unit for CC-LINK Network
・CC-Link-AnyWireASLINK Bridge Unit
Model

NZ2AW1C2AL

OpenFieldBus side
Support protocol

Corresponding CC-Link Ver. 1.10, Ver. 2.00 (Switched by setting)Standard price (¥)

Sold by Mitsubishi Electric Corporation

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC)
Current 0.2[A] (when 128 slave units are connected, not including load current)

Power supply

Transmission line driver:(Supplied to front panel terminal)

Number of occupied
stations

Set to Ver. 1.10 (1 station, 2 stations, 3 stations, 4 stations selected) or Ver. 2.00 (4 stations fixed, expanded 2 times setting)Outer dimensions (mm)105.5(H) x 43.0(W) x 86.0(D)

Mass

200g
Interface

・CC-Link IE Field－AnyWireASLINK Bridge Unit
Model

NZ2AW1GFAL

OpenFieldBus side
Support protocol

Corresponding CC-Link IE Field

Power supply

Transmission line driver:(Supplied to front panel terminal)

Outer dimensions (mm)105.5(H) x 43.0(W) x 86.0(D)Master units /Terminator

ASLINKMASTER

Bridge Unit

Standard price (¥)

Sold by Mitsubishi Electric Corporation

GatewayInterface for PC

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC)
Current 0.3[A] (when 128 slave units are connected, not including load current)
Mass

Resend Unit
Bridge for
AnyWire DB A20

200g

Terminator*Master unit = ASLINKMASTER, slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKAMP, ASLINKSENSOR)

AnyWireASLINK System

20

Master units /TerminatorInterface

ASLINKMASTER*For common function specifications, see page 14.

◆ Gateway for Open Network
・AnyWireASLINK DeviceNet Gateway*2
Model

B2G78-D1

OpenFieldBus side
Support protocol

Corresponding DeviceNet

Power supply

Transmission line driver:(Supplied to front panel terminal)

Outer dimensions (mm)105.8(H) × 43.0(W) × 86.0(D)Standard price (￥)Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.15[A] (when 128 slave units are connected, not including load current)
Mass

190g

Standard price (￥)Open

・AnyWireASLINK PROFIBUS Gateway*2

Bridge Unit

Model

B2G78-PB1

Gateway

OpenFieldBus side
Support protocol

Corresponding PROFIBUS

Interface for PC

Power supply

Transmission line driver:(Supplied to front panel terminal)

Outer dimensions (mm)105.8(H) × 43.0(W) × 86.0(D)Resend Unit

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.15[A] (when 128 slave units are connected, not including load current)
Mass

190g

Standard price (￥)Open

Bridge for
AnyWire DB A20
Terminator

Open

・AnyWireASLINK Ethernet Gateway*2
Model

B2G78-E1

OpenFieldBus side
Support protocol

SLMP (Seamless Message Protocol)
EtherNet/IP
Modbus/TCP Response command(0x02) Read Discrete Inputs: BIT IN, (0x01) Read Coils: BIT OUT, (0x05) Write Single Coil: BIT OUT(0x04) Read Input Registers: WORD IN, (0x03) Read Holding Registers: WORD OUT(0x06) Write Single Register: WORD OUT, (0x10) Read Multiple Registers: WORD OUT

Power supply

Transmission line driver:(Supplied to front panel terminal)

Outer dimensions (mm)105.8(H)×43.0(W)×86.0(D)Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.15[A] (when 128 slave units are connected, not including load current)
Mass

190g

*2 Contact our sales division for digital link function relationship of B2G78-D1, B2G78-PB1 and B2G78-E1.

◆ Master Interface for PC Bus
・AnyWireASLINK Master I/F for PCI Express *3
Model

B2P8-E01

PCI Express side
specification

PCI Express 2.0 compatible (Gen 2) x1 lane (usable with x1, x4, x8, x16 slots)
Low profile compatible (brackets for low profile and standard profile are included)

Power supply

Transmission line driver:(Supplies to connector terminal on
bracket surface)

Outer dimensions (mm)67.9(W)x167.6(D) (Only Master I/F board section)

Standard price (￥)Open

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)Mass

65g (when installed with a low profile bracket)*3 For information regarding B2P8-E01 digital function compatibility, please contact our sales division.

◆ Resend Unit
・AnyWireASLINK resend unit *4
Model

BR27-01

Product
specifications

Transmission between input terminal and output terminal with the same address setting is conducted.

Power supply

Transmission line driver:(Supplies to connector terminal)

Outer dimensions (mm)40.0(H)×100.0(W)×48.0(D)Standard price (￥)OpenEx.) When an input is made into the input terminal with address of 50, the output signal is automatically transmitted to the output terminal
with address of 50.

MODE

Resend Unit

BR27-01

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)
Mass

200g

*4 For information regarding BR27-01 digital function compatibility, please contact our sales division.

*Master unit = ASLINKMASTER, slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKAMP, ASLINKSENSOR)

21

AnyWireASLINK System

*For common function specifications, see page 14.

◆ Bridge for AnyWire DB A20
・AnyWireASLINK bridge for DB A20 series *5
Model

AB27-AL

Product
specifications

AnyWire DB A20 series (dedicated protocol for AnyWire BUS)

Power supply

Transmission line driver:(Supplies to connector terminal)

Outer dimensions (mm)40.2(H)×100.0(W)×40.0(D)(Can be used only for 31.3 kHz setting. Only one unit can be connected.)

ASLINK Bridge

AB27-ALSET

RDY LINK

LINK SET ALM

FG 24V 0V D G

DP DN

FG 24V 0V

DP DN

D

G

Open

Standard price (￥)Master units /Terminator

ASLINKMASTER

Voltage 24[V] DC +15 to -10% (21.6 to 27.6[V] DC) Ripple 0.5[V]p-p max.
Current 0.1[A] (when 128 slave units are connected, not including load current)
69g

Mass

*5 For information regarding AB27-AL digital function compatibility, please contact our sales division.
Interface
Bridge Unit

Terminator (Terminator for AnyWireASLINK)

GatewayInterface for PC◆Terminator (Waveform shaping module)

Resend Unit

Unit: mmTERMINATOR
VCT AWG19×2-wire (2-core)

BT0

Terminator

Dedicated adaptor (included)
ＡＤＰ－Ａ０３

3.2
1.5
24.5

Black: DN
Red: DP

（300）

BT0

12
16

1.5

44

2-φ7 (Depth 1.7)

24.5

2-φ3.2

Installation drawing for ADP-A03

TERMINATOR

12.25

20
44

BT0-12

UL style 2103
2-core×No.24AWG (Black) φ4.1
2

1

3

4

38
14

1 N/C
2 DP
3 N/C
4 DN

Bridge for
AnyWire DB A20

2：DP
3：NC

1：NC
4：DN

LINK

BT0-12

Color: Warm grayTransmission cable

BT0-12

7.5

XS5H

（200）

BT0-C

UL style 2103
2-core×No.24AWG (Black) φ4.1

38

Red: DP

DP:赤DN:黒Black: DN

LINK

BT0-C

7.5

BT0-C

14

TERMINATOR

（200）

*

is a registered trademark of OMRON Corporation.

Dimensions (mm)44×24.5×12

BT０

Open

Transmission waveform shaping module (with polarity) M12 connector connection (IP67)

14×38×7.5

BT０-12

OpenTransmission waveform shaping module (with polarity) cable connection (IP67)

14×38×7.5

BT０-C

Open

ADP-81

Open

BTO-12 and BTO-C mounting dedicated adaptor (4 adaptors included)

ModelStandardprice(￥)

Product specifications
Transmission waveform shaping module (with polarity) cable connection (mounting adaptor is included)*The dimensions are numerical values excluding the cable section.

*Master unit = ASLINKMASTER, slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKAMP, ASLINKSENSOR)

AnyWireASLINK System

22

23

AnyWireASLINK System

Engineering tool
GX Works2

Introduction of address writer and tool required for configuration of system
Address Writer・・・・・・25

GX Works2・・・・・・26

24

Engineering Tool

Address Writer◆ Address Writer

Unit: mm

ADDRESS WRITER

ARW-04

19

61

100

Address writer
ARW-04 appearance
Address Writer
GX Works2

Remote head
ARW-RH appearance
Product specifications
Address setting
Parameter setting
Teaching[Reading/writing]

ModelStandardprice (￥)Non-contact setting portable tool by infrared communication
7 segment display, driven by dry battery

ARW-04

Open

Infrared remote head for setting address,
parameter in narrow locations

ARW-RHOpen

Address writer ARW-04 + infrared remote head

ARW-04-RH

Open

Details◆ Desktop Address Writer

Unit: mm

150（3） （62.79）

ARW-D04（4.94）ADDRESS WRITER（64.75）

Product specifications

Address setting
Parameter setting
Teaching[Reading/writing]

Details
Address setting, parameter setting and teaching byinfrared communications or parameter setting throughtransmission line Dry batteries or AC adaptor drive
Transmission line extension cable for ARW-D04(50cm with 4-pole LP connectors on both ends
Transmission line extension cable for ARW-D04(50cm with 4-pole LP connector-M12 connector)

200

Model

Standardprice (￥)ARW-D04

Open

ARW-EX-L4L4Open

ARW-EX-L412

Open*It is necessary to connect with the transmission line (LP connector connection/push terminal connection) even when setting by infrared communication.

See page 163 for details on the address writer and desktop address writer.

25

AnyWireASLINK System

◆ GX Works2
AnyWireASLINK is compatible with iQSS, which allows the sensor state to be easily monitored andadjusted in the engineering environment “GX Works2” of Mitsubishi Electric Corporation.

Monitoring of sensor state

Adjustment of set values

Engineering Tool

GX Works2 (Engineering software)

・MELSEC sequencer

Backup/restoration of set values
Address Writer・GOT

GX Works2

Easy
startup

System configuration diagram is automatically created.
Each slave unit can be set from the system configuration diagram.
・Slave units are automatically detected andadded to the system configuration diagram.
・Troubleshooting is easy! Error codes andprocessing content are displayed.
・State of slave unit can be easily grasped.

Easy
programming

Function block (FB), sample ladders and sample screens allow for easy programming.

FB (function block) are available to download from MELSOFT Library corner on the Mitsubishi Electric Corporation FA website.
For details of GW Works2 and iQSS, contact Mitsubishi Electric Corporation.

AnyWireASLINK System

26

27

AnyWireASLINK System

Accessories /Special Units

Introduction of cables, connectors and filter convenient for system configuration
Transmission Cable and Connector・・・・・・29
Branch Unit (IP67)

・・・・・・31

Cabtire Cable (IP67)

・・・・・・31

Filter・・・・・・32

28

Accessories /Special Units

Accessories◆ AnyWire Cable/Connector (AnyWire transmission cable & connector)
Product specifications

Standard
price (¥)

DetailsModel

2-core flat cable (AWG16 (1.25sq)×2-core, insulating coating outer diameter φ2.5±0.1mm)

FK2-125-100Open2-core flat cable (AWG18 (0.75sq)×2-core, insulating coating outer diameter φ2.5±0.1mm)

FK2-075-100Open

4-core flat cable (AWG16 (1.25sq)×4-core, insulating coating outer diameter φ2.5±0.1mm)

FK4-125-100Open

4-core flat cable (AWG18 (0.75sq)×4-core, insulating coating outer diameter φ2.5±0.1mm)

FK4-075-100

OpenFor 2-core flat cable (1.25sq) (Coating outer diameter φ2.54mm Cover: Black Body: Red)

LP2-BR-10P

Open

For 2-core flat cable (0.75sq) (Coating outer diameter φ2.54mm Cover: Black Body: Black)

LP2-BK-10P

OpenFor cabtire cable (Coating outer diameter φ1.8 to 2.1mm Cover: yellow Body: Gray)

LP2-YEG-10P

Open

For cabtire cable (Coating outer diameter φ1.4 to 1.7mm Cover: Pink Body: White)

LP2-PWH-10P

Open

Branch Unit (IP67)

For 4-core flat cable (1.25sq) (Coating outer diameter φ2.54mm Cover: White Body: Red) Pin protector type

LP4-WR-10P

Open

Cabtire Cable (IP67)

For 4-core flat cable (0.75sq) (Coating outer diameter φ2.54mm Cover: White Body: Black) Pin protector type

LP4-WH-10P

Open

For cabtire cable (Coating outer diameter φ1.1 to 1.4mm Cover: White Body: White)

LP4-OR-10P

Open

For cabtire cable (Coating outer diameter φ2.1 to 2.4mm Cover: Orange Body: Black)

LP4-YE-10P

OpenFor cabtire cable (Coating outer diameter φ1.8 to 2.1mm Cover: Yellow Body: Black)

LP4-ORG-10P

Open

For cabtire cable (Coating outer diameter φ2.1 to 2.4mm Cover: Orange Body: Gray)

LP4-YEG-10P

Open

For cabtire cable (Coating outer diameter φ1.8 to 2.1mm Cover: Yellow Body: Gray)

LP4-WW-10POpen

4-core flat cable (for 1.25 sq) with a built-in 4-pole e-CON
socket(Coating outer diameter φ2.54mm Cover: Black Body: Red)

LE4-BR-10POpen

4-core flat cable (for 1.25 sq) with a built-in 4-pole e-CON socket(Coating outer diameter φ2.54mm Cover: Black Body: Red)

LE4-BR-100P

Open

Crimping tool for LP/LE
connector

Crimping tool dedicated to LP/LE connector(The connector can be crimped by pliers, etc., however,a dedicated tool is recommended)

LP-TOOLOpen

T attachment (100 pieces are included)

For 4-core flat cable (1.25sq)(coating outer diameter φ2.54mm for 1.25sq-1.25sq branching)

TA4-GB-100P

Open

For 4-core flat cable (1.25sq)(coating outer diameter φ2.54mm for 1.25sq-0.3sq branching)

TA4-WB-100P

Open

Crimping tool dedicated for T attachment (The connector can be
crimped by pliers, etc., however, a dedicated tool is recommended)
For sensor connection(0.14 to less than 0.3sq, Coating outer diameter φ0.8 to 1.0mm Color: Red)For sensor connection(0.14 to less than 0.3sq, Coating outer diameter φ1.0 to 1.2mm Color: Yellow)
For sensor connection(0.14 to less than 0.3sq, Coating outer diameter φ1.2 to 1.6mm Color: Orange)
For sensor connection(0.3 to 0.5sq, Coating outer diameter φ1.0 to 1.2mm Color: Green)
For sensor connection(0.3 to 0.5sq, Coating outer diameter φ1.2 to 1.6mm Color: Blue)For sensor connection(0.3 to 0.5sq, Coating outer diameter φ1.6 to 2.0mm Color: Gray)

TA-TOOLOpen

EP4-RE-8P

Open

EP4-YE-8P

Open

EP4-OR-8P

Open

EP4-GR-8P

Open

EP4-BL-8P

Open

EP4-GL-8P

Open

Crimping tool dedicated to EP connector(The connector can be crimped by pliers, etc., however,a dedicated tool is recommended)

EP-TOOL

Open

Flat cable (100m winding)(1.25sq = Conductor resistance 0.015Ω/m･Allowable current 12.7A)(0.75sq = Conductor resistance 0.025Ω/m･Allowable current 7A)(Image on page at right.)*Crimp type link connector(Allowable current 5A)

LP4-WR-10P

Filter

LP2-PWH-10P

Body color
Red: for wire diameter size 1.25sq
Black: for wire diameter size 0.75sq
Gray: for wire diameter size 0.5sq
White: for wire diameter size 0.3sq

LE connector(10 connectors included)*Crimp type e-CON connection
link connector

LE connector (100 connectors included)*Crimp type e-CON connection link connector* This cannot be inserted andremoved after connection.

Crimping tool for T attachment
EP connector(8 connectors are included)* Crimp type sensor connector(Used for e-CON connection type (4-pole))

EP4-BL-8P

EP4-RE-8P

compliantCrimping tool for EP
connector

29

AnyWireASLINK System

4 pole typeTransmission Cable
and Connector

2 pole type

LP connector(10 connectors included)

Accessories /Special Units

Accessories◇ Flat cable appearance photo

2-core flat cable

AWG16 (1.25sq)×2-core(DN:DP from the left)

2-core flat cable

AWG18 (0.75sq)×2-core(DN:DP from the left)

4-core flat cable

AWG16 (1.25sq)×4-core(DN:DP:0V:24V from the left)

4-core flat cable

AWG18 (0.75sq)×4-core(DN:DP:0V:24V from the left)

When using the combination of the dedicated flat cable and LP connector (link connector), connect wires so that theblack electric wire (DN line) is on the hinge side (No.1) of the connector cover as shown in the photo 1.

Photo 1Furthermore, if 2-core and 4-core cables are mixed, they can be mutually connected by using an LP connector (linkconnector) for a 4-core cable even for a 2-core cable. In that case, also set electric wires so that the black electric wire
(DN line) is on No.1 of the connector cover as shown in the photo 2, and connect wires as No. 3/4 are kept blank.

Transmission Cable
and Connector
Branch Unit (IP67)
Cabtire Cable (IP67)
FilterPhoto 2

“Correspondence table of AnyWireASLINK and applicable connectors” is provided on page 165. See the table when selecting connectors.

AnyWireASLINK System

30

Accessories /Special Units

Others Units◆ Branch unit (IP67) With M12 connector straight plug
Unit: mm

BL2109-04-22

BRANCH UNIT

2-R2.25

View A

3

4

2-φ4.5 bore

A
73

20

Lot display

25.5

4.2
AWG16
φ8.2

(1000)

Transmission Cable
and Connector

BRANCH UNIT

Branch Unit (IP67)
Cabtire Cable (IP67)
Filter390.5

3

2-R2.25
2×φ9 counterbore, depth 11

2-φ4.5 bore

4
50

A
42

33
4.2

77.3

AWG16
φ8.2

20

34
B

Lot display

25.5
View B
2
1

9BL2109-08-22
Product specifications

4

1 24V
2 DP
3 0V
4 DN

BL2109-08-22

View A
2
1

1 24V
2 DP
3 0V
4 DN

B

View B
2
1
9BL2109-04-22

2×φ9 counterbore, depth 11

50

1

33

2

42

1 24V
2 DP
3 0V
4 DN

(1000)

135.5

4

Details

3

1 24V
2 DP
3 0V
4 DN

Standard
price (¥)

Model

Branch unit (IP67)

4 ports

BL2109-04-22

Open

With M12 connector straight plug

8 ports

BL2109-08-22

Open◆ Cabtyre cable (IP67) (1.25sq) With M12 connector
CABLE

Unit: mm

BL2-1S1P-□K（3000）： BL2-1S1P-3K（5000）： BL2-1S1P-5K（10000）： BL2-1S1P-10K

40.7

2 1 24V
2 DP
3 0V
3 4 DN1

BL2-1S1P-□K

4

CABLE

XS5F (Socket)
Color: Warm gray

φ14.9

φ14.9

44.7

XS5H (Plug)Color: Warm gray
UL style 2464
4-core×No.16AWG(Black) φ8.2

1 24V
2 DP
3 0V
4 DN

2

1

3

4

BL2-0C1S-3K（3000）

24

BL2-0C1S-3K
Product specifications

3

φ14.9

1

40.7

XS5F (Socket)
Color: Warm gray

1 24V
2 DP
3 0V
4 DN

Details

UL style 2464
4-core×No.16AWG(Black) φ8.2

ModelBlack: DN
Red: DPWhite: 0V
Brown: 24V

Standard
price (¥)

Cabtyre cable

Straight socket M12/straight plug M12, 3m

BL2-1S1P-3K

Open(IP67) (1.25sq)

Straight socket M12/straight plug M12, 5m

BL2-1S1P-5K

Open

With M12 connector

Straight socket M12/straight plug M12, 10m

BL2-1S1P-10K

Open

4-core discrete-wire/straight socket M12, 3m

BL2-0C1S-3K

Open*When connecting an M12 connector spec waterproof cable as a trunk line or branch line when using various slave devices compatible with IP67
(IP66), use our products listed above (such as BL2-1S1P) with an internal wiring spec of 1.25sq wherever possible. If you would like to use asmaller wire diameter waterproof cable for routing, the OMRON XS5 series is recommended (As the internal wiring is 0.5sq, it is necessary to pay
attention to the DP-DN allowable supply current value when using an XS5 series waterproof cable totaling 10m or longer for one system. Pleasecontact us for details). Furthermore, as some XS5 series products cannot be used, please contact our technical support service listed at the end of
this booklet or our sales division.
*

31

AnyWireASLINK System

is a registered trademark of OMRON Corporation.

◆ Filter
Unit: mm

ANF-01(11)(2.5)
2-Protective earth (PE)

12

15

92
77

6-M4

Hook
Mounting plate

DIN railTransmission Cable
and Connector

7

(9)

41

■DIN rail installation example

8(2)

Terminal cover knob

27

53

FILTER

Accessories /Special Units

Filter（Filter for AnyWireASLINK)

Branch Unit (IP67)
Cabtire Cable (IP67)

Product specifications
Filter for 24V line

Dimensions (mm)ModelStandard price (¥)

92×53×41

ANF-01Open

Filter*Use this filter when total extension of DP, DN, 24V and 0V lines exceed 50m in a power supply system to be supplied.
*Thoroughly check the specifications with the Product Guide.

AnyWireASLINK System

32

33

AnyWireASLINK System

Slave Units (I /O)

I/O terminals compatible with general-purpose I/O equipment
ASLINKER

SmartLINKER (Disconnection Detection LINKER)・・・・・・35
ASLINKER

Cable TypeASLINKER

M12 Connector Type・・・・・・39
・・・・・・47

ASLINKTERMINAL

Small Terminal Block Terminal (8/16 Points) ・・・・・・49
ASLINKTERMINAL

Integrated Small Terminal (4/8/16 Points) ・・・・・・61
ASLINKTERMINAL

Small 8-Point Terminal
ASLINKTERMINAL

Relay Terminal
ASLINKTERMINAL

・・・・・・65
・・・・・・69

Manifold Driver・・・・・・70

List of Specifications

・・・・・・71

34

Slave Units (I/O)

ASLINKER◆ SmartLINKER (Disconnection detection LINKER)
SmartLINKER is an ultra-small I/O terminal that can diagnose output line disconnection, power line
short-circuit, power line disconnection and O volt line disconnection in real time while operating 2-wireand 3-wire type sensors. This provides strong support for prompt recovery of the system.

ASLINKER
SmartLINKER

Disconne

ction??

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal

uit !?

cShort-cir

ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driverndles
Full off wbirues!!

Just attach
SmartLINKER
to thesensor used.

Slimmed-downwith Sho-Haisen !!

o

List of Specifications

Disconnected!

Here!

Where?

Intelligent Sho-Haisen that can detect sensor disconnection
and short-circuit in real time
The answer is

SmartLINKER

35

AnyWireASLINK System

Detection of sensor cable disconnection
ASLINKER of AnyWireASLINK monitors disconnection of 2-wire sensor cable connected and notifies thesequencer.
SmartLINKER is also available for 3-wire sensor disconnection.
This function helps identify the cause and location of disconnection even when it cannot be seen from outside,
providing support for prompt recovery.

Slave Units (I/O)

ASLINKER

ASLINKER
SmartLINKER

Information
notification!

Input error!

POWER

INPUT
100-200VAC

Disconnection!

ON

No.1

OFF

No.2

ON

No.3

ON

ASLINKER
M12/M8 Cable Type

LJ51AW12BY
RUN LINK SET ALM

SET

AnyWireNo.0

ASLINKER
M12/M12 Cable Type

Disconnection of
sensor connected
detected!
1

Abnormal location
identified promptlywith use of GOT

ASLINKTERMINAL
Small Terminal Block Terminal

ON

No.1

OFF

No.2

ON

ASLINKTERMINAL
Relay

No.3

ON

ASLINKTERMINAL
Manifold Driver

青：0V IN1

LINK 茶：24VL
IN0
0
黒：IN
1

ASLINKER
M12 Connector Type

No.0
LINK 茶：24VL
IN0
0
黒：IN

Error!
Position: Address 1
Type: ASLINKER
Status: I/O disconnection

ASLINKER
Cable Type

青：0V IN1

ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal

List of Specifications

Detection of power line short-circuit of 3-wire type sensor
SmartLINKER monitors power line short-circuit of sensor cable connected, and cuts off from the trunk line whenshort-circuit occurs.
Thanks to this function, stop of the entire system for a long time due to power failure can be avoided in case of
power line short-circuit.
What’ s more, notification from SmartLINKER allows for prompt identification of abnormal location.

Power line
short-circuit

POWER

INPUT
100-200VAC

LJ51AW12BY
RUN LINK SET ALM

SET

AnyWireInformation
notification!
Short-circuit detected
and cut off from thetrunk line!

No.0
No.1
No.2
No.3

Power failure!

No.0
Error!
Position: Address 1
Type: ASLINKER
Status: Power wire short-circuit!

Abnormal location
identified promptlywith use of GOT

LINK 茶：24VL
IN0
0
黒：IN
1

青：0V IN1

No.1
No.2
LINK 茶：24VL
IN0
0
黒：IN
1

青：0V IN1

No.3

AnyWireASLINK System

36

Slave Units (I/O)

ASLINKER◆ SmartLINKER (Disconnection detection LINKER)＜ Outline Dimensional Drawings ＞
B2N87SB-02D□-CC20
UL style 2844
3-core×No.26AWG (Black) φ3.1

UL style 2103
2-core×No.24AWG (Black) φ4.1

4.5

ASLINKER
SmartLINKER

60
56

Red: DP

Brown: 24VBlack: IN
Blue: 0V

Black: DN

（200）

4.5
（200）

7.1

Brown: 24VBlack: IN
Blue: 0V

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeTransmission side:
4-wire type

ASLINKER
Cable TypeASLINKER

ASLINKER
M12 Connector TypeBL2LN87SB-02D□-CC20

UL style 20276
4-core×No.24AWG (Gray) φ4.1

ASLINKTERMINAL
Manifold Driver
List of Specifications

7.1

Brown: 24VBlack: IN
Blue: 0V

Core wire
coatingouterdiameter
φ1.0

（200）

4.5

Adaptor ADP-87
ASLINKER canbe mounted withscrews using theadaptor.

ASLINKTERMINAL
Relay

60
56

Red: DPBlack: DN
Green: 24V
White: 0V

6.5

17

ASLINKTERMINAL
Small 8-Point Terminal

9.2
13.4

5.5

ASLINKTERMINAL
Integrated Small Terminal

UL style 2844
3-core×No.26AWG (Black) φ3.1

10.2

ASLINKTERMINAL
Small Terminal Block TerminalCore wire
coatingouterdiameter
φ1.0

6.5

17

13.4

5.5

Transmission side:
2-wire typeCore wire coatingouter diameter
9.2
φ1.5

10.2

ASLINKER

Unit: mm

4.5
（200）

Core wire coatingouter diameter
φ1.1

Brown: 24VBlack: IN
Blue: 0V

＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 17×60×9.2

Model
B2N87SB-02D-CC20

2Consumption
current (mA)
Transmission I/O
side
side

Input

Mass resistance/
1 point Per 1 Per 1 Response Standard(g)point common
price(¥)time(kΩ)

2-wire type

A

20

6.8

Max. 1ms

Open

2-wire type

A

20

6.8

Max. 1ms

Open

10.0

4-wire type

A

20

6.8

Max. 1ms

Open

9.2

4-wire type

A

20

6.8

Max. 1ms

Open

DC input NPN 3.4

Connection(non-insulation)

B2N87SB-02DS-CC20

2

DC input PNP 3.4

BL2LN87SB-02D-CC20

2

DC input NPN 1.5

BL2LN87SB-02DS-CC20

2

ADP-87ASLINKER mounting dedicated adaptor (4 adaptors included)

DC input PNP 1.5

Output max.
ON current (mA)

Dimension(mm)

Number of Input/
I/O points output
Input Output specifications

Method／ : Not applicable －: Not determined(non-insulation)(insulation)(insulation)

Open*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

37

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKER＜ LED indication ＞
B2N87SB-02D□-CC20

Target model

Indication status

LED symbol

LINK On(Green)Flashing

ALM
(Red)

BL2LN87SB-02D□-CC20

Target model

Detailed status

LED symbol

Indication status

LINK On(Green)Flashing

Transmission signal error
Transmission signal reception
No transmission signal

Off(including disconnection and reverse connection of DP and DN)

On

I/O short-circuit or disconnection

Flashing

Slave unit voltage decrease

Detailed status
Transmission signal error
Transmission signal reception
No transmission signal

Off(including disconnection and reverse connection of DP and DN)

On

I/O disconnection, I/O short-circuit,
I/O voltage decrease

Flashing

Slave unit voltage decrease

ASLINKER
SmartLINKER

Off

NormalASLINKER
M12/M12 Cable Type

LINK
ALM

Alternate flashing
LINK
ALM

When master unit detects that the
ID (address) of this unit is duplicatedor not set

ASLINKER
M12/M8 Cable Type

I/O

On

Input ON

ALM
(Red)

Off

NormalLINK
ALM

Alternate flashing
LINK
ALM

When master unit detects that the
ID (address) of this unit is duplicatedor not set

I/O

On

Input ON

Off

Input ON

Off

Flashing

Flashing in synchronization with LINK
in case of I/O disconnection

Input ON

Flashing

Flashing in synchronization with LINK
in case of I/O disconnection

ASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal

B2N87SB-02D□-CC20
BL2LN87SB-02D□-CC20

ASLINKTERMINAL
Small 8-Point TerminalLED
indication unit

ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver＜ Circuit diagram ＞
Target model

List of Specifications

B2N87SB-02D□-CC20

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24VL and IN)
OFF voltage: 8V or less (between 24VL and IN)
24VL supply current: 50mA Max. (each point)(between 24VL and 0VL)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0VL)
OFF voltage: 8V or less (between IN and 0VL)
24VL supply current: 50mA Max. (each point)(between 24VL and 0VL)

Control circuitControl circuit

24VL

24VL

(Brown)IN

DN(Black)6.8k(Black)0VL(Blue)
SmartLINKER side

Target model(Blue)
Sensor side
(The circuit diagram isa typical example.)

Current detection

Sensormain circuit

0VL

DP
(Red)

Internal circuit

6.8k (Black)Sensormain circuit

DN(Black)(Brown)IN

Internal circuit

DP
(Red)

SmartLINKER side

Sensor side
(The circuit diagram isa typical example.)

Current detection

BL2LN87SB-02D□-CC20

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24VL and IN)
OFF voltage: 8V or less (between 24VL and IN)
24V allowable current: 50mA Max. (each point)(between 24VL and 0VL)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0VL)
OFF voltage: 8V or less (between IN and 0VL)
24VL allowable current : 50mA Max. (each point)(between 24VL and 0VL)
Control circuitControl circuit

24VL

DP
(Red)

6.8k (Black)Sensormain circuit

IN

Internal
circuit

DN(Black)0VL(Blue)

0V(White)SmartLINKER side
Current detection

Functional icon indication*See page 15 fordetails on function.

(Brown)24V(Green)Sensor side
(The circuit diagram isa typical example.)

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

DP
(Red)
DN
(Black)INInternal
circuit(Brown)6.8k(Black)0VL(Blue)

0V(White)SmartLINKER side
Current detection

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensormain circuit

24VL
24V
(Green)Sensor side
(The circuit diagram isa typical example.)

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

38

Slave Units (I/O)

ASLINKER◆ M12/M12 cable type (IP67)＜ Outline Dimensional Drawings ＞
BL287□B-02F-2D220 /BL287□B-02FS-2D220

ASLINKERUL style 20276
4-core×No.23AWG φ4.6 GrayUL style 2844
3-core×No.26AWG φ3.1 Black

BL287SB-02F-2D220

BL287XB-02F-2D220

1

3BL287XB-02F-2D220

4

1 24V
2 DP
3 0V
4 DN

ASLINKER
M12/M12 Cable Type

LINK
IN
OUT
ALM

ADDRESS No.

XS5F

IN
OUT

OUT0

Transmission cable
XS5H

IN0

1

2

4

3

1

2

4

3

7.5

UL style 2844
2-core×No.26AWG φ3.1 Black

17

7.5

2.2

ASLINKER
SmartLINKER

17

38

Color: Warm gray2

Unit: mm

（200）

（200）
（280）

ASLINKER
M12/M8 Cable TypeTerminal layout (input) Terminal layout (output/NPN) Terminal layout (output/PNP)

ASLINKER
Cable Type

BL287PB-02F-2D220

ASLINKER
M12 Connector Type

Adaptor ADP-87
ASLINKER can be mountedwith screws using the adaptor.

ASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal

Connector color/black Connector color/warm gray Connector color/warm gray
PIN No. Content PIN No. Content PIN No. Content
1
24V
1
24V
1
N/C
2
N/C
2
N/C
2
N/C
3
0V
3
N/C
3
0V
* This drawing shows case of input/output terminal.
4
IN
4
OUT
4
OUT

Transmission side: M12
I/O side: M12

ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 17×38×7.5／ : Not applicable －: Not determined

Model
BL287SB-02F-2D220

2BL287SB-02FS-2D220

2BL287XB-02F-2D220

1BL287XB-02FS-2D220

1BL287PB-02F-2D220
BL287PB-02FS-2D220

DC input NPN

Consumption
current (mA)
Transmission I/O
side
side

3.4

Output max.
Input
ON current (mA)
Mass resistance/
1 point Per 1 Per 1 Response(g)point common
time
(kΩ)

11.2

4-wire type

A

45

6.8

Connection(insulation)

Standard
price(¥)

Max. 1ms

Open

3.4

11.2

4-wire type

A

45

6.8

Max. 1ms

Open

1 Tr output NPN 3.5

8.0

4-wire type

A

45

6.8

100

100 Max. 1ms

Open

3.6

8.0

4-wire type

A

45

6.8

100

100 Max. 1ms

Open

2 Tr output NPN 3.8

4.7

4-wire type

A

45

100

200 Max. 1ms

Open

4.7

4-wire type

A

45

100

200 Max. 1ms

Open

DC input PNP
DC input /DC input /1 Tr output PNP

2 Tr output PNP 3.8

ADP-87

Dimension(mm)

Number of Input/
I/O points output
Input Output specifications

MethodNon-insulation only

(insulation)(insulation)(insulation)(insulation)(insulation)Open

4-wire type ASLINKER mounting dedicated adaptor (4 adaptors included)*The dimensions are numerical values excluding the cable section.

*Contact our sales division if you would like to request products of connector and cable specifications other than the above.
*ASLINKER M12/M18 cable type (IP67) of 2-wire (non-insulation) can be made according to order.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

39

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units (I/O)

ASLINKER＜ LED indication ＞
Indication status

LED symbol

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

Detailed status

BL287□B-02F□-2D220

Transmission signal error
Transmission signal reception

LED
indication unit

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
I/O
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver＜ Circuit diagram ＞

List of Specifications

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN)
OFF voltage: 8V or less (between 24V and IN)
24V allowable current: 50mA Max. (Sum of values at two points)(between 24V and 0V)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V)
OFF voltage: 8V or less (between IN and 0V)
24V allowable current: 50mA Max. (Sum of values at two points)(between 24V and 0V)

24V

DP

Internal circuit

6.8k

DP
(Red)

IN

22k

DN

24V

24V
(Green)Internal circuit

24V

6.8k
IN
22k

DN
(Black)0V

0V

0V(White)0V

NPN output circuit

PNP output circuit<Circuit requirements><Circuit requirements>

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (Between 24V and 0V)(Sum of values at two points)

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (Between 24V and 0V)(Sum of values at two points)

24V

24k

22k

DP

OUT

DN

DN

0V

0V

22k

OUT

Load

Internal circuit

24V

Load

22k

DP

Internal circuit

24V

0V

(In case of inductive load, install a surge killer.)

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

40

Slave Units (I/O)

ASLINKER◆ M12 / M8 cable type (IP67)＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKER BL287□B-02F□-2D820 /BL287□B-02F□-2D720
UL style 2844
3-core×No.26AWG φ3.1 BlackUL style 20276
4-core×No.23AWG φ4.6 Gray

ASLINKER
M12/M12 Cable Type

4

BL287XB-02F-2D820

LINK
IN
OUT
ALM

17

1

3

ADDRESS No.

IN0

3

XS3F

IN
OUT

Transmission cable
UL style 2844
XS5H
2-core×No.26AWG φ3.1 Black

1 24V
2 DP
3 0V
4 DN

1

(In case of 3 poles)
4

OUT0

3

1

7.5

2.2

ASLINKER
SmartLINKER

2(In case of 4 poles)
4
2

7.5

BL287SB-02F-2D820

38

Color: Warm gray

17

（200）

（200）
（280）

ASLINKER
M12/M8 Cable TypeTerminal layout (input) Terminal layout (output/NPN) Terminal layout (output/PNP)

BL287XB-02F-2D820

ASLINKER
Cable TypeASLINKER
M12 Connector TypeTransmission side: M12
I/O side: M8

ASLINKTERMINAL
Small Terminal Block Terminal* This drawing shows case of input/output terminal.

Connector color/black Connector color/warm gray Connector color/warm gray
PIN No. Content PIN No. Content PIN No. Content
1
24V
1
24V
1
N/C
2
N/C
2
N/C
2
N/C
3
0V
3
N/C
3
0V
4
IN
4
OUT
4
OUT
* There is no PIN No.2 in case of 3 poles.

ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay

Adaptor ADP-87
ASLINKER can be mountedwith screws using the adaptor.

ASLINKTERMINAL
Manifold Driver
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 17×38×7.5／ : Not applicable －: Not determined

Model
BL287SB-02F-2D820

2

DC input NPN
DC input PNP
DC input /Tr output NPN
DC input /Tr output PNP
DC input NPN

BL287SB-02FS-2D820

2BL287XB-02F-2D820

1BL287XB-02FS-2D820

1BL287SB-02F-2D720 Note 1)

2

1
1

Consumption
current (mA)
Transmission I/O
side
side

Dimension(mm)

Number of Input/
I/O points output
Input Output specifications

MethodNon-insulation only

Output max.
Input
ON current (mA)
Mass resistance/
1 point Per 1 Per 1 Response(g)point common
time
(kΩ)

11.2

4-wire type

A

35

6.8

3.4

11.2

4-wire type

A

35

6.8

3.5

8.0

4-wire type

A

35

6.8

100

3.6

8.0

4-wire type

A

35

6.8

100

100 Max. 1ms

Open

3.4

11.2

4-wire type

A

35

6.8

Max. 1ms

Open

3.4

11.2

4-wire type

A

35

6.8

Max. 1ms

Open

3.5

8.0

4-wire type

A

35

6.8

100

100 Max. 1ms

Open

8.0

4-wire type

A

35

6.8

100

100 Max. 1ms

Open

3.4

Connection(insulation)(insulation)(insulation)(insulation)(insulation)

BL287SB-02FS-2D720 Note 1)

2

BL287XB-02F-2D720 Note 2)

1

BL287XB-02FS-2D720 Note 2)

1

ADP-87

4-wire type ASLINKER mounting dedicated adaptor (4 adaptors included)1
1

DC input PNP
DC input /Tr output NPN
DC input /Tr output PNP

3.6(insulation)(insulation)(insulation)

Standard
price(¥)

Max. 1ms

Open

Max. 1ms

Open

100 Max. 1ms

Open

Open

Note 1): M8 connector specification is 3 poles.
Note 2): M8 connector specification is 3 poles for input, and 4 poles for output.
*The dimensions are numerical values excluding the cable section.

*Contact our sales division if you would like to request products of connector and cable specifications other than the above.
*ASLINKER M12/M18 cable type (IP67) of 2-wire (non-insulation) can be made according to order.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

41

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units (I/O)

ASLINKER＜ LED indication ＞
Indication status

LED symbol

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

Detailed status

BL287□B-02F□-2D820
BL287□B-02F□-2D720

Transmission signal error
Transmission signal reception

LED
indication unit

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
I/O
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver＜ Circuit diagram ＞

List of Specifications

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN)
OFF voltage: 8V or less (between 24V and IN)
24V allowable current: 50mA Max. (Sum of values at two points)(between 24V and 0V)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V)
OFF voltage: 8V or less (between IN and 0V)
24V allowable current: 50mA Max. (Sum of values at two points)(between 24V and 0V)

24V

DP

Internal circuit

6.8k

DP
(Red)

IN

22k

DN

24V

24V
(Green)Internal circuit

24V

6.8k
IN
22k

DN
(Black)0V

0V

0V(White)0V

NPN output circuit

PNP output circuit<Circuit requirements><Circuit requirements>

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (Between 24V and 0V)(Sum of values at two points)

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (Between 24V and 0V)(Sum of values at two points)

24V

24k

22k

DP

OUT

DN

DN

0V

0V

22k

OUT

Load

Internal circuit

24V

Load

22k

DP

Internal circuit

24V

0V

(In case of inductive load, install a surge killer.)

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

42

Slave Units (I/O)

ASLINKER◆ Cable type 2-wire type＜ Outline Dimensional Drawings ＞
B281□B-02U-CC20 /B281□B-02US-CC20

UL style 2103
2-core×No.24AWG (Black) φ4.1

38

Red: DP

Brown: 24VBlack: IN
Blue: 0V14

2.2

UL style 2844
3-core×No.26AWG φ3.1 Black
14

ASLINKER（200）
Mounting dedicatedadaptor fitting state■ADP-81 (mounting adaptor) dimensions
10.4
40.2
2-φ6
1 3.5
4
4

ASLINKER
M12 Connector TypeASLINKTERMINAL
Integrated Small Terminal

10.2

17.2

ASLINKTERMINAL
Small Terminal Block Terminal

2-φ3.5
1.7 1.5

ASLINKTERMINAL
Relay

Adaptor ADP-81
ASLINKER can be mounted with screws
using the adaptor.

ASLINKTERMINAL
Manifold Driver

2.4

15
5

ASLINKTERMINAL
Small 8-Point Terminal

Brown: 24V / Black: OUT0Black: OUT0/Blue: 0V
Brown: 24V / Black: OUT1
Black: OUT1/Blue: 0V

Mounting dedicatedadaptor fitting state

1

5

Cut when coupling to use.

R1.2

Output：
B281PB-02U-CC20 /
B281PB-02US-CC20

Core wire coatingouter diameter
φ1.0

3.5

ASLINKER
Cable Type

Brown: 24VBlack: IN
Blue: 0V

（200）

7.5

Transmission side: 2-wire type

ASLINKER
M12/M8 Cable TypeBlack: OUT
Blue: 0V

7.5

Core wire coatingouter diameter φ1.5

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input：
B281SB-02U-CC20 /B281SB-02US-CC20
Brown: 24VBlack: IN
Blue: 0V

Brown: 24VBlack: OUT

Black: DN
7.5

Unit: mm

* This drawing shows case of input/output terminal.

List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 14×38×7.5

B281SB-02U-CC20

2

B281SB-02US-CC20

2

B281XB-02U-CC20

1

B281XB-02US-CC20

1Consumption
current (mA)
Transmission I/O
side
side

DC input NPN 15.4

B281PB-02US-CC20

DC input PNP 13.5
DC input /2-wire type

A

15

6.8

2-wire type

A

15

6.8

2-wire type

A

15

6.8

100

2-wire type

A

15

6.8

100

100 Max. 1ms

Open

2-wire type

A

15

100

100 Max. 1ms

Open

2-wire type

A

15

100

100 Max. 1ms

Open

Connection(non-insulation)

1 Tr output NPN 10.5

(non-insulation)

DC input /1 Tr output PNP 10.1

(non-insulation)(non-insulation)

2 Tr output PNP 6.5

ADP-81

Output max.
Input
ON current (mA)
Mass resistance/
1 point Per 1 Per 1 Response(g)point common
time
(kΩ)

(non-insulation)

2 Tr output NPN 5.5

B281PB-02U-CC20

Dimension
(mm)

Model

Method／ : Not applicable －: Not determined

Number of Input/
I/O points output
Input Output specifications(non-insulation)

Standard
price(¥)

Max. 1ms

Open

Max. 1ms

Open

100 Max. 1ms

Open

Open

2-wire type ASLINKER mounting dedicated adaptor (2 adaptors included)*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

43

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKER＜ LED indication ＞
LED symbol

Indication status

LINK(Green) Flashing

LINK
ALM

Transmission signal reception

Off(including disconnection and
No transmission signal reverse connection of DP and DN)

On

I/O short-circuit or disconnection

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

On
I/O
(Orange)
Off
ALM
LINK
I/O

B281□B-02U□-CC20

Transmission signal error

On

ALM
(Red)

Detailed status

On

ALM

LINK
Flashing IN

LEDindication unit

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input OFFASLINKER
Cable TypeShows I/O disconnection when IN
flashes in synchronization with LINK
when ALM is lit.

ASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver＜ Circuit diagram ＞

List of Specifications

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24VL and IN)
OFF voltage: 8V or less (between 24VL and IN)
24VL supply current: 50mA Max. (each point)(between 24VL and 0VL)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0VL)
OFF voltage: 8V or less (between IN and 0VL)
24VL supply current: 50mA Max. (each point)(between 24VL and 0VL)

24VL

24VL

DP

Internal circuit

DP

DN

Internal circuit

6.8k
IN

DN

Current detection

Current detection

0VL

NPN output circuit

6.8k

IN

0VL

PNP output circuit<Circuit requirements><Circuit requirements>

Withstand voltage: DC30V
Maximum ON current : 100mA (each point)

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (each point)

24VL
DP

Internal circuit

OUT

OUT

Load

Internal circuit

Load

DP

DN

DN

Current detection

Current detection

0VL(In case of inductive load, install a surge killer.)

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

44

Slave Units (I/O)

ASLINKER◆ Cable type 4-wire type＜ Outline Dimensional Drawings ＞
BL287□B-02F-CC20 /BL287□B-02FS-CC20
UL style 2844
3-core×No.26AWG (Black) φ3.1

UL style 20276
4-core×No.23AWG (Gray) φ4.6
Black: DN
Red: DP2.2 White: 0V
Brown: 24V

Brown: 24V/
Black: IN
Blue: 0V

17

38

17

ASLINKER

7.5

（200）

Transmission side: 4-wire type

Mounting dedicatedadaptor fitting state

ASLINKER
Cable Type

Brown: 24VBlack: IN
Blue: 0V
Output：BL287PB-02F-CC20 /BL287PB-02FS-CC20
Brown: 24V / Black: OUT0（200）

Black: OUT0/Blue: 0V
Brown: 24V / Black: OUT1
Black: OUT1/Blue: 0VCore wire coatingouter diameter
φ1.0

3.5

ASLINKER
M12/M8 Cable TypeBlack: OUT
Blue: 0V

7.5

ASLINKER
M12/M12 Cable Type

Input：
BL287SB-02F-CC20 /BL287SB-02FS-CC20
Brown: 24VBlack: IN
Blue: 0V

Brown: 24V/
Black: OUT

Core wire coatingouter diameter φ1.4

7.5

ASLINKER
SmartLINKER

Unit: mm

■ADP-87 (mounting adaptor) dimensions

ASLINKER
M12 Connector Type

40.2
4

11
Mounting dedicatedadaptor fitting state

20.2

ASLINKTERMINAL
Small Terminal Block Terminal

2φ
3.

5

ASLINKTERMINAL
Integrated Small Terminal

5

5

1.7

ASLINKTERMINAL
Small 8-Point Terminal

2φ6

15

ASLINKTERMINAL
Relay

Adaptor ADP-87
ASLINKER can be mounted with screws
using the adaptor.

ASLINKTERMINAL
Manifold Driver

Cut when coupling to use.

R1.2

* This drawing shows case of input/output terminal.

List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 17×38×7.5

BL287SB-02F-CC20

2BL287SB-02FS-CC20

2BL287XB-02F-CC20

1BL287XB-02FS-CC20

1BL287PB-02F-CC20
BL287PB-02FS-CC20

DC input NPN

Consumption
current (mA)
Transmission I/O
side
side

3.4

Output max.
Input
ON current (mA)
Mass resistance/
1 point Per 1 Per 1 Response(g)point common
time
(kΩ)

11.2

4-wire type

A

18

6.8

Connection(insulation)

Standard
price(¥)

Max. 1ms

Open

3.4

11.2

4-wire type

A

18

6.8

Max. 1ms

Open

1 Tr output NPN 3.5

8.0

4-wire type

A

18

6.8

100

100 Max. 1ms

Open

3.6

8.0

4-wire type

A

18

6.8

100

100 Max. 1ms

Open

2 Tr output NPN 3.8

4.7

4-wire type

A

18

100

200 Max. 1ms

Open

4.7

4-wire type

A

18

100

200 Max. 1ms

Open

DC input PNP
DC input /DC input /1 Tr output PNP

2 Tr output PNP 3.8

ADP-87

Dimension
(mm)

Model

Method／ : Not applicable －: Not determined

Number of Input/
I/O points output
Input Output specifications(insulation)(insulation)(insulation)(insulation)(insulation)Open

4-wire type ASLINKER mounting dedicated adaptor (4 adaptors included)*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

45

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKER＜ LED indication ＞
Indication status

LED symbol

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

Detailed status

BL287□B-02F□-CC20

Transmission signal error
Transmission signal reception

LED
indication unit

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
I/O
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver＜ Circuit diagram ＞

List of Specifications

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN)
OFF voltage: 8V or less (between 24V and IN)
24V allowable current: 50mA Max. (Sum of values at two points)(between 24V and 0V)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V)
OFF voltage: 8V or less (between IN and 0V)
24V allowable current: 50mA Max. (Sum of values at two points)(between 24V and 0V)

24V

DP

Internal circuit

6.8k

DP
(Red)

IN

22k

DN

24V

24V
(Green)Internal circuit

24V

6.8k
IN
22k

DN
(Black)0V

0V

0V(White)0V

NPN output circuit

PNP output circuit<Circuit requirements><Circuit requirements>

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (Between 24V and 0V)(Sum of values at two points)

Withstand voltage: DC30V
Maximum ON current : 100mA
24V allowable current : Maximum 500mA (Between 24V and 0V)(Sum of values at two points)

24V

24k

22k

DP

OUT

DN

DN

0V

0V

22k

OUT

Load

Internal circuit

24V

Load

22k

DP

Internal circuit

24V

0V

(In case of inductive load, install a surge killer.)

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

46

Slave Units (I/O)

ASLINKER◆ M12 Connector Type (IP67)＜ Outline Dimensional Drawings ＞

Unit: mm

B280□B-02U-C1220 /B280□B-02US-C1220

ASLINKERUL style 2103
2-core×No.24AWG (Black) φ4.1

M12 waterproof connector(Socket)

Red: DP

φ14.5

Black: DN

ASLINKER
SmartLINKER

Transmission side: Cable

ASLINKER
M12/M12 Cable TypeI/O side: M12 (Female)

ASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal

50.5Core wire coatingouter diameter φ1.5

（200）
B280SB-02U-C1220 /B280SB-02US-C1220

1：24VL

2：IN1

4：IN0

3：0VL

B280XB-02U-C1220 /B280XB-02US-C1220

1：24VL

2：OUT0

4：IN0

3：0VL

B280PB-02U-C1220 /B280PB-02US-C1220

1：24VL

2：OUT1

4：OUT03：0VL

SampleASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay

65

Size comparison of ASLINKER

ASLINKTERMINAL
Manifold Driver
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : φ14.5×65

Input, output only
(2 points simultaneous detection not allowed)

Consumption
current (mA)
Transmission I/O
side
side

B280SB-02U-C1220

2

DC input NPN 15.4
DC input PNP 13.5
DC input /1 Tr output NPN 10.5
DC input /1 Tr output PNP 10.1

B280SB-02US-C1220

2

B280XB-02U-C1220

1

B280XB-02US-C1220

1

B280PB-02U-C1220

2 Tr output NPN 5.5

B280PB-02US-C1220

2 Tr output PNP 6.5

Dimension
(mm)

Model

Method／ : Not applicable －: Not determined

Number of Input/
I/O points output
Input Output specifications

Output max.
Input
ON current (mA)
Mass resistance/
1 point Per 1 Per 1 Response(g)point common
time
(kΩ)

2-wire type

A

22

6.8

2-wire type

A

22

6.8

2-wire type

A

22

6.8

100

2-wire type

A

22

6.8

100

100 Max. 1ms

Open

2-wire type

A

22

100

100 Max. 1ms

Open

2-wire type

A

22

100

100 Max. 1ms

Open

Connection(non-insulation)(non-insulation)(non-insulation)(non-insulation)(non-insulation)(non-insulation)

Standard
price(¥)

Max. 1ms

Open

Max. 1ms

Open

100 Max. 1ms

Open*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

47

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKER＜ LED indication ＞
LED symbol

Indication status

LINK(Green) Flashing

LINK
ALM

Transmission signal reception

Off(including disconnection and
No transmission signal reverse connection of DP and DN)

On

I/O short-circuit or disconnection

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

On
I/O
(Orange)
Off
ALM
LINK
I/O

B280□B-02U□-C1220

Transmission signal error

On

ALM
(Red)

Detailed status

On

ALM

LINK
Flashing IN

LEDindication unit

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input OFFASLINKER
Cable TypeShows I/O disconnection when IN
flashes in synchronization with LINK
when ALM is lit.

ASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver＜ Circuit diagram ＞

List of Specifications

NPN input circuit

PNP input circuit<Circuit requirements><Circuit requirements>

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between 24VL and IN)
OFF voltage: 8V or less (between 24VL and IN)
24V supply current: 50mA Max. (each point)(between 24VL and 0VL)

Rated input voltage: DC24V
Maximum switching current : 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0VL)
OFF voltage: 8V or less (between IN and 0VL)
24V supply current: 50mA Max. (each point)(between 24VL and 0VL)

24VL

24VL

DP

Internal circuit

DP

DN

Internal circuit

6.8k
IN

DN

Current detection

IN

0VL

Current detection

0VL

NPN output circuit

6.8k

PNP output circuit<Circuit requirements><Circuit requirements>

Withstand voltage: DC30V
Maximum ON current : 100mA (each point)

Withstand voltage: DC30V
Maximum ON current : 100mA (each point)

24VL
DP

Internal circuit

OUT

OUT

Load

Internal circuit

Load

DP

DN

DN

Current detection

Current detection

0VL(In case of inductive load, install a surge killer.)

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

48

Slave Units (I/O)

ASLINKTERMINAL◆ Small Terminal Block Terminal (Cable type 3-wire type sensor compatible)

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Adaptor ADP-108
ASLINKTERMINAL can be mounted on
the DIN rail using the adaptor.

ASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal

ASLINKTERMINAL
Relay＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 28.9×81×39.4／ : Not applicable －: Not determined

ASLINKTERMINAL
Manifold Driver

Number of
I/O points

Input/
outputInput Output specifications

Model

List of Specifications

BL296SB-08F-V50

Consumption
current (mA)
Transmission I/Oside side8

DC input NPN 6 40

BL296SB-08FS-V50

8BL296XB-08F-V50

4BL296XB-08FS-V50

4

DC input PNP 6 40
DC input /Tr output NPN 6 26
DC input /4 Tr output PNP 6 26

4BL296PB-08F-V50

8 Tr output NPN 6 10BL296PB-08FS-V50

8 Tr output PNP 6 10BL296SB-08F-3-V50

8

DC input NPN 6 40

BL296SB-08FS-3-V50

8BL296XB-08F-3-V50

4BL296XB-08FS-3-V50

4DC input PNP 6 40
DC input /4 Tr output NPN 6 26
DC input /4 Tr output PNP 6 26

BL296PB-08F-3-V50

8 Tr output NPN 6 10BL296PB-08FS-3-V50

8 Tr output PNP 6 10BL296SB-08F-11-V50

8

DC input NPN 6 40

BL296SB-08FS-11-V50

8BL296XB-08F-11-V50

4BL296XB-08FS-11-V50

4

DC input PNP 6 40
DC input /4 Tr output NPN 6 26
DC input /4 Tr output PNP 6 26

BL296PB-08F-11-V50

8 Tr output NPN 6 10BL296PB-08FS-11-V50

8 Tr output PNP 6 10

ADP-108

Connection
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

Terminal
block type

Dimension
(mm)
Mass
(g)

ASLINKTERMINAL
Small 8-Point Terminal

MethodASLINKTERMINAL
Integrated Small Terminal

Standard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal block

Output max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
point common
(kΩ)
time
price (￥)A 90 6.8
A 90 6.8

Max. 1ms

Open

Max. 1ms

Open

A 90 6.8

100

400 Max. 1ms

Open

A 90 6.8

100

400 Max. 1ms

Open

A 90

100

800

Max. 1ms

Open

A 90

100

800 Max. 1ms

Open

A 85 6.8

Max. 1ms

Open

A 85 6.8

Max. 1ms

Open

Max. 1ms

Open

A 85 6.8

100

400

A 85 6.8

100

400 Max. 1ms

Open

A 85

100

800

Max. 1ms

Open

A 85

100

800 Max. 1ms

Open

A 85 6.8

Max. 1ms

Open

A 85 6.8

Max. 1ms

Open

Max. 1ms

Open

A 85 6.8

100

400

A 85 6.8

100

400 Max. 1ms

Open

A 85

100

800

Max. 1ms

Open

A 85

100

800 Max. 1ms

Open
Open

DIN rail adaptor for fitting ASLINKTERMINAL small terminal block terminal (1 set included)*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

49

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL＜ LED indication ＞
LED symbol

Indication status

Detailed status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

LED
indication unit

BL296□B-08F□-V50
BL296□B-08F□-3-V50
BL296□B-08F□-11-V50

Transmission signal error
Transmission signal reception

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector Type＜ Circuit diagram ＞

ASLINKTERMINAL
Small Terminal Block Terminal

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V)
OFF voltage: 8V or less (between IN and 0V)

Switch,sensor, etc.
(2-wire type)
0V

24V

IN

0V

0V
4-wire (insulation) type ASLINK terminal(AnyWire based power source)<Circuit requirements>
DN

Load

(Output terminal)

DN<Circuit requirements>
Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

Load

(Output side of input/output terminal)

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

OUT

0V

0V

24V
DP

Control circuit

Internal circuit

24V*In case of inductive load, install a surge killer.

OUT

IN

0V

DN

0V

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

OUT

0V

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detectionIN
0V

Load by external power source

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

Sensing
level
monitoring

24V

0V

Load by external power source

Hi
LO
NG

Load by external power source<Circuit requirements>

OUT

24V

O
F
F

0V

0V

【PNP output circuit 2】

24V

O
N

IN

0V

24V

*See page 15 fordetails on function.

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

Internal circuit

DP

24V

0V

Load by external power source

24V

24V

Control circuit

IN

0V

Functional icon indication

0V

Load

0V

DN

DP

0V

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

DP

24V

Control circuit

Internal circuit

OUT*In case of inductive load, install a surge killer.

OUT

0V

24V

(Output side of input/output terminal)

DN

0V

24V

【NPN output circuit 2】

24V

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA

Load by external power source*In case of inductive load, install a surge killer.

24V

DN

0V

24V

<Circuit requirements>*In case of inductive load, install a surge killer.

DP

0V【PNP output circuit 1】

OUT

0V

IN

Control circuit

Withstand voltage: 30V DC
Maximum ON current: 100mA

Internal circuit

DP

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

24V

(Output terminal)

24V
6.8k

0V

Load by external power source

List of Specifications

0V

Internal circuit【NPN output circuit 1】

DN

0V

ASLINKTERMINAL
Manifold Driver

IN

24V

DP

OUT

ASLINKTERMINAL
Relay

Switch,sensor, etc.
(2-wire type)

6.8k

0V

Internal circuit

DN

6.8k

DN

24V
24V

Internal circuit

DP

DP

Load

24V

)

<Circuit requirements>

Control circuit(

IN

Internal circuit

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN) 0V
OFF voltage: 8V or less (between 24V and IN)

6.8k

ASLINKTERMINAL
Small 8-Point Terminal

24V

24V

Internal circuit

DP<Circuit requirements>

Input terminal
Input side of input/output terminalInternal circuit)【PNP input circuit】

24V

24V

Control circuit(

Input terminal
Input side of input/output terminalInternal circuit【NPN input circuit】

ASLINKTERMINAL
Integrated Small Terminal

In case of PNP method

Internal circuitin case of NPN method

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

50

Slave Units (I/O)

ASLINKTERMINAL◆ Small Terminal Block Terminal (Cable type 3-wire type sensor compatible)＜ Outline Dimensional Drawings ＞
ASLINKTERMINAL

Unit: mm

BL296□B-08F□-V50

39.4
28.6
19.5

(49)※1
39.4
28.6
17

24V 0V 24V 0V 24V 0V 24V 0V
0 1 2 3 4 5 6 7

ASLINKER
SmartLINKER

ASLINKER
M12/M8 Cable TypeUL style 20276
4-core×No.24AWG (Gray) φ4.6

ASLINKER
M12 Connector Type

1 3

5

(500)

ASLINKER
Cable Type3.
2-φCore wire coatingouter diameter φ1.4

2

5
4

7
6

9
8

28.9

81
74.5

ASLINKER
M12/M12 Cable Type11 13 15

10 12 14 16

6.5

6.5
66.62

ASLINKTERMINAL
Small Terminal Block Terminal(0.69)ASLINKTERMINAL
Integrated Small Terminal

ASLINKTERMINAL
Relay

32.2

Black: DN
Red: DPWhite: 0V
Green: 24V

ASLINKTERMINAL
Small 8-Point Terminal*1 State when terminal
block cover is opened

ASLINKTERMINAL
Manifold Driver(0.69)

List of Specifications*Example of BL296PB-08F-V50. BL296□B-08F□-V50 also has the same dimensions.

BL296□B-08F□-3-V50

17

39.4
28.6

39.4
28.6
19.5

ASLINKTERMINAL

24V 0V 24V24V 0V 24V24V 0V 24V24V 0V 24V
0 1 0V 2 3 0V 4 5 0V6 7 0V

81
74.5

Core wire coatingouter diameter φ1.4

28.9

(500)

UL style 20276
4-core×No.24AWG (Gray) φ4.6
24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V
5

3.
2-φ

8

8
62.06

(1.47)(1.47)

36

Black: DN
Red: DPWhite: 0V
Green: 24V
0 1 0V 2 3 0V 4 5 0V 6 7 0V

*Example of BL296PB-08F-3-V50. BL296□B-08F□-3-V50 also has the same dimensions.

Functional icon indication*See page 15 fordetails on function.

51

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Slave Units (I/O)

ASLINKTERMINAL

Unit: mm

BL296□B-08F□-11-V50

17

39.4
28.6

39.4
28.6
19.5

ASLINKTERMINAL

24V 0V 24V24V 0V 24V24V 0V 24V24V 0V 24V
0 1 0V 2 3 0V 4 5 0V 6 7 0V

ASLINKER
SmartLINKER

81
74.5

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeCore wire coatingouter diameter φ1.4

ASLINKER
Cable Type

28.9

(500)

UL style 20276
4-core×No.24AWG (Gray) φ4.6

5
3.
2-φ

8

ASLINKER
M12 Connector Type

8ASLINKTERMINAL
Small Terminal Block Terminal

64.07(0.18)(0.75)

Black: DN
Red: DPWhite: 0V
Green: 24V

ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal

24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V

ASLINKTERMINAL
Relay

28.6

0 1 0V 2 3 0V 4 5 0V 6 7 0V

ASLINKTERMINAL
Manifold Driver
List of Specifications*Example of BL296PB-08F-11-V50. BL296□B-08F□-11-V50 also has the same dimensions.

ADP-108 (mounting dedicated DIN rail adaptor) dimensions●Fitted state

95
81

20.4

35.5

35.5

7
15

7.6
(11.1)

39.4

15

7
15

7.5

3.6

8

15

5.3

5.3
7.6
(11.1)

828.9

2-φ3.574.5

40.8

ASLINKTERMINAL*Example of BL296PB-08F-11-V50. Other models also have the same dimensions as indicated.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

52

Slave Units (I/O)

ASLINKTERMINAL◆ Small Terminal Block Terminal (Cable type 3-wire type sensor compatible)

ASLINKER
SmartLINKER

Adaptor ADP-108

ASLINKER
M12/M12 Cable TypeASLINKTERMINAL can be mounted on
the DIN rail using the adaptor.

ASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal

ASLINKTERMINAL
Relay＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 28.9×141×39.4／ : Not applicable －: Not determined

ASLINKTERMINAL
Manifold Driver

Number of
I/O points Input/
outputInput Output specifications

Model

List of Specifications

Consumption
current (mA)
Transmission I/Oside side

BL296SB-16F-V50

16

DC input NPN 8 80

BL296SB-16FS-V50

16

BL296XB-16F-V50

8BL296XB-16FS-V50

8

DC input PNP 8 80
DC input /Tr output NPN 8 50
DC input /8 Tr output PNP 8 50

8BL296PB-16F-V50

16 Tr output NPN 8 15BL296PB-16FS-V50

16 Tr output PNP 8 15BL296SB-16F-3-V50

16

DC input NPN 8 80

BL296SB-16FS-3-V50

16

BL296XB-16F-3-V50

8BL296XB-16FS-3-V50

8

DC input PNP 8 80
DC input /8 Tr output NPN 8 50
DC input /8 Tr output PNP 8 50

BL296PB-16F-3-V50

16 Tr output NPN 8 15BL296PB-16FS-3-V50

16 Tr output PNP 8 15BL296SB-16F-11-V50

16

DC input NPN 8 80

BL296SB-16FS-11-V50

16

BL296XB-16F-11-V50

8BL296XB-16FS-11-V50

8

DC input PNP 8 80
DC input /8 Tr output NPN 8 50
DC input /8 Tr output PNP 8 50

BL296PB-16F-11-V50

16 Tr output NPN 8 15BL296PB-16FS-11-V50

16 Tr output PNP 8 15

ADP-108

Connection
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

Terminal
block type

Dimension
(mm)
Mass
(g)

ASLINKTERMINAL
Small 8-Point Terminal

MethodASLINKTERMINAL
Integrated Small Terminal

Standard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal block

Output max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
point common
(kΩ)
time
price (￥)A 150 6.8
A 150 6.8

Max. 1ms

Open

Max. 1ms

Open

A 150 6.8

100

800 Max. 1ms

Open

A 150 6.8

100

800 Max. 1ms

Open

A 150

100 1600 Max. 1ms

Open

A 150

100 1600 Max. 1ms

Open

A 145 6.8

Max. 1ms

Open

A 145 6.8

Max. 1ms

Open

Max. 1ms

Open

A 145 6.8

100

800

A 145 6.8

100

800 Max. 1ms

Open

A 145

100 1600 Max. 1ms

Open

A 145

100 1600 Max. 1ms

Open

A 140 6.8

Max. 1ms

Open

A 140 6.8

Max. 1ms

Open

Max. 1ms

Open

A 140 6.8

100

800

A 140 6.8

100

800 Max. 1ms

Open

A 140

100 1600 Max. 1ms

Open

A 140

100 1600 Max. 1ms

Open
Open

DIN rail adaptor for fitting ASLINKTERMINAL small terminal block terminal (1 set included)*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

53

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL＜ LED indication ＞
LED symbol

Indication status

Detailed status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

LED
indication unit

BL296□B-16F□-V50
BL296□B-16F□-3-V50
BL296□B-16F□-11-V50

Transmission signal error
Transmission signal reception

1

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

3
2

5
4

11 13 15 17 19 21 23 25 27 29 31

9

7
6

8

10 12 14 16 18 20 22 24 26 28 30 32(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector Type＜ Circuit diagram ＞

ASLINKTERMINAL
Small Terminal Block Terminal

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V)
OFF voltage: 8V or less (between IN and 0V)

Switch,sensor, etc.
(2-wire type)
0V

24V

IN

0V

0V
4-wire (insulation) type ASLINK terminal(AnyWire based power source)<Circuit requirements>
DN

Load

(Output terminal)

DN<Circuit requirements>
Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

Load

(Output side of input/output terminal)

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

OUT

0V

0V

24V
DP

Control circuit

Internal circuit

24V*In case of inductive load, install a surge killer.

OUT

IN

0V

DN

0V

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

OUT

0V

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detectionIN
0V

Load by external power source

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

Sensing
level
monitoring

24V

0V

Load by external power source

Hi
LO
NG

Load by external power source<Circuit requirements>

OUT

24V

O
F
F

0V

0V

【PNP output circuit 2】

24V

O
N

IN

0V

24V

*See page 15 fordetails on function.

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

Internal circuit

DP

24V

0V

Load by external power source

24V

24V

Control circuit

IN

0V

Functional icon indication

0V

Load

0V

DN

DP

0V

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

DP

24V

Control circuit

Internal circuit

OUT*In case of inductive load, install a surge killer.

OUT

0V

24V

(Output side of input/output terminal)

DN

0V

24V

【NPN output circuit 2】

24V

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA

Load by external power source*In case of inductive load, install a surge killer.

24V

DN

0V

24V

<Circuit requirements>*In case of inductive load, install a surge killer.

DP

0V【PNP output circuit 1】

OUT

0V

IN

Control circuit

Withstand voltage: 30V DC
Maximum ON current: 100mA

Internal circuit

DP

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

24V

(Output terminal)

24V
6.8k

0V

Load by external power source

List of Specifications

0V

Internal circuit【NPN output circuit 1】

DN

0V

ASLINKTERMINAL
Manifold Driver

IN

24V

DP

OUT

ASLINKTERMINAL
Relay

Switch,sensor, etc.
(2-wire type)

6.8k

0V

Internal circuit

DN

6.8k

DN

24V
24V

Internal circuit

DP

DP

Load

24V

)

<Circuit requirements>

Control circuit(

IN

Internal circuit

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN) 0V
OFF voltage: 8V or less (between 24V and IN)

6.8k

ASLINKTERMINAL
Small 8-Point Terminal

24V

24V

Internal circuit

DP<Circuit requirements>

Input terminal
Input side of input/output terminalInternal circuit)【PNP input circuit】

24V

24V

Control circuit(

Input terminal
Input side of input/output terminalInternal circuit【NPN input circuit】

ASLINKTERMINAL
Integrated Small Terminal

In case of PNP method

Internal circuit

In case of NPN method

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

54

Slave Units (I/O)

ASLINKTERMINAL◆ Small Terminal Block Terminal (Cable type 3-wire type sensor compatible)＜ Outline Dimensional Drawings ＞

Unit: mm

19.5

39.4

28.6

BL296□B-16F□-V50

ASLINKTERMINAL

24V 0V 24V 0V 24V 0V 24V 0V 24V 0V 24V 0V 24V 0V 24V 0V
0 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15(49)※1ASLINKER
SmartLINKER

134.5

28.6

ASLINKER
M12/M12 Cable Type2-φ3.5

141

39.4
17
R/W

19.5

1

ASLINKER
Cable Type

3
2

LINK

4

0

ALM

5
6

2

1

3

4

5

6

7

8

9 10 11 12 13 14 15

11 13 15 17 19 21 23 25 27 29 31

97

10 12 14 16 18 20 22 24 26 28 30 32

8

ASLINKER
M12 Connector Type

28.9

ASLINKER
M12/M8 Cable Type119.53

ASLINKTERMINAL
Integrated Small Terminal

141

UL style 20276
4-core×No.24AWG (Gray) φ4.6

(500)

ASLINKTERMINAL
Small Terminal Block Terminal

127.5932.2

ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay

BL296PB-16F-V50

Black: DN
Red: DPWhite: 0V
Green: 24V

ASLINKTERMINAL
Manifold Driver
List of Specifications

7.62*1 State when terminal
block cover is opened*Example of BL296PB-16F-V50. BL296□B-16F□-V50 also has the same dimensions.

19.5

28.6

BL296□B-16F□-3-V50

24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V
0

1 0V

2

3 0V 4

5 0V 6

39.4
28.6
17

7 0V 8

9 0V 10 11 0V 12 13 0V 14 15 0V

141

2-φ3.5134.5

R/W

LINK ALM 0

1

2

3

4

5

6

7

8

9

10 11 12 13 14 15

24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V24V0V 24V141

UL style 20276
4-core×No.24AWG (Gray) φ4.6

(500)

28.9

39.4

ASLINKTERMINAL

123.020

1 0V 2

3 0V 4

5 0V 6

7 0V 8

9 0V 10 11 0V 12 13 0V 14 15 0V

BL296PB-16F-3-V50

Black: DN
Red: DPWhite: 0V
Green: 24V*Example of BL296PB-16F-3-V50. BL296□B-16F□-3-V50 also has the same dimensions.

Functional icon indication*See page 15 fordetails on function.

55

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Unit: mm

19.5

28.6

BL296□B-16F□-11-V50

39.4

24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V
0

1

0V

2

3

0V

4

5

0V

6

7

39.4

0V

8

9

0V 10 11

0V 12 13

0V 14 15 0V

141

28.6

2-φ3.5

134.5

17
R/W

LINK ALM 0

1

2

3

4

5

6

ASLINKER
SmartLINKER

7

8

9

10 11 12 13 14 15

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable Type

28.9

ASLINKTERMINAL

Slave Units (I/O)

ASLINKTERMINALASLINKER
Cable TypeASLINKER
M12 Connector Type(500)

ASLINKTERMINAL
Small Terminal Block Terminal

141

UL style 20276
4-core×No.24AWG (Gray) φ4.6

124.46ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal

28.6

24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V 24V 0V 24V

0

1

0V

2

3

0V

4

5

0V

6

7

0V

8

9

0V 10 11 0V 12 13 0V 14 15 0V

ASLINKTERMINAL
Relay

BL296PB-16F-11-V50

ASLINKTERMINAL
Manifold DriverBlack: DN
Red: DPWhite: 0V
Green: 24V

List of Specifications*Example of BL296PB-16F-11-V50. BL296□B-16F□-11-V50 also has the same dimensions.

ASLINKTERMINAL

ADP-108 (mounting dedicated DIN rail adaptor) dimensions●Fitted state
155
141
134.5
4

5

6

7

8

9

10 11 12 13 14 15

28.9

3

8

8

15

15

7
15

20.4

7
15

40.8

2

35.5

1

7.6
24V0V 24V24V 0V 24V 24V 0V 24V24V 0V 24V 24V0V 24V24V 0V 24V24V 0V 24V24V 0V 24V(11.1)

0

1

0V

2

3 0V

4

5 0V

6

7

0V

8

9

0V 10 11 0V 12 13 0V 14 15 0V

7.5

BL296PB-16F-11-V50

39.4(11.1)LINK ALM 0

3.6

7.6

5.3

5.3

35.5

R/W

2-φ3.5*Example of BL296PB-16F-11-V50. Other models also have the same dimensions as indicated.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

56

Slave Units (I/O)

ASLINKTERMINAL◆ Small Terminal Block Terminal

ASLINKER
SmartLINKER

Adaptor ADP-108

ASLINKER
M12/M12 Cable TypeASLINKTERMINAL can be mounted on
the DIN rail using the adaptor.

ASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal

ASLINKTERMINAL
Relay＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimensionA : 28.9×81×39.4／ : Not applicable －: Not determined

ASLINKTERMINAL
Manifold Driver

Number of
I/O points

Input/
outputInput Output specifications

Model

List of Speciﬁcations

BL296SB-08F

Consumption
current (mA)
Transmission I/Oside side8

DC input NPN 6 40

BL296SB-08FS

8

BL296XB-08F

4

BL296XB-08FS

4

DC input PNP 6 40
DC input /Tr output NPN 6 26
DC input /4 Tr output PNP 6 26

4BL296PB-08F

8 Tr output NPN 6 10BL296PB-08FS

8 Tr output PNP 6 10BL296SB-08F-3

8

DC input NPN 6 40

BL296SB-08FS-3

8BL296XB-08F-3

4

BL296XB-08FS-3

4

DC input PNP 6 40
DC input /4 Tr output NPN 6 26
DC input /4 Tr output PNP 6 26

BL296PB-08F-3

8 Tr output NPN 6 10BL296PB-08FS-3

8 Tr output PNP 6 10BL296SB-08F-11

8

DC input NPN 6 40

BL296SB-08FS-11

8

BL296XB-08F-11

4

BL296XB-08FS-11

4

DC input PNP 6 40
DC input /4 Tr output NPN 6 26
DC input /4 Tr output PNP 6 26

BL296PB-08F-11

8 Tr output NPN 6 10BL296PB-08FS-11

8 Tr output PNP 6 10

ADP-108

Connection
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

Terminal
block type

Dimension
(mm)
Mass
(g)

ASLINKTERMINAL
Small 8-Point Terminal

MethodASLINKTERMINAL
Integrated Small Terminal

Standard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal blockStandard
terminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal block
Springterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal blockEuroterminal block

Output max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
point common
(kΩ)
time
price (￥)A 75 6.8
A 75 6.8

Max. 1ms

Open

Max. 1ms

Open

A 75 6.8

100

400 Max. 1ms

Open

A 75 6.8

100

400 Max. 1ms

Open

A 75

100

800

Max. 1ms

Open

A 75

100

800 Max. 1ms

Open

A 70 6.8

Max. 1ms

Open

A 70 6.8

Max. 1ms

Open

Max. 1ms

Open

A 70 6.8

100

400

A 70 6.8

100

400 Max. 1ms

Open

A 70

100

800

Max. 1ms

Open

A 70

100

800 Max. 1ms

Open

A 65 6.8

Max. 1ms

Open

A 65 6.8

Max. 1ms

Open

Max. 1ms

Open

A 65 6.8

100

400

A 65 6.8

100

400 Max. 1ms

Open

A 65

100

800

Max. 1ms

Open

A 65

100

800 Max. 1ms

Open
Open

DIN rail adaptor for fitting ASLINKTERMINAL small terminal block terminal (1 set included)*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

57

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL＜ LED indication ＞
LED symbol

Indication status

Detailed status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

LED
indication unit

BL296□B-08F□
BL296□B-08F□-3BL296□B-08F□-11

Transmission signal error
Transmission signal reception

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector Type＜ Circuit diagram ＞

ASLINKTERMINAL
Small Terminal Block Terminal

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V)
OFF voltage: 8V or less (between IN and 0V)

Switch,sensor, etc.
(2-wire type)
0V

24V

IN

0V

0V
4-wire (insulation) type ASLINK terminal(AnyWire based power source)<Circuit requirements>
DN

Load

(Output terminal)

DN<Circuit requirements>
Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

Load

(Output side of input/output terminal)

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

OUT

0V

0V

24V
DP

Control circuit

Internal circuit

24V*In case of inductive load, install a surge killer.

OUT

IN

0V

DN

0V

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

OUT

0V

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detectionIN
0V

Load by external power source

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

Sensing
level
monitoring

24V

0V

Load by external power source

Hi
LO
NG

Load by external power source<Circuit requirements>

OUT

24V

O
F
F

0V

0V

【PNP output circuit 2】

24V

O
N

IN

0V

24V

*See page 15 fordetails on function.

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

Internal circuit

DP

24V

0V

Load by external power source

24V

24V

Control circuit

IN

0V

Functional icon indication

0V

Load

0V

DN

DP

0V

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

DP

24V

Control circuit

Internal circuit

OUT*In case of inductive load, install a surge killer.

OUT

0V

24V

(Output side of input/output terminal)

DN

0V

24V

【NPN output circuit 2】

24V

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA

Load by external power source*In case of inductive load, install a surge killer.

24V

DN

0V

24V

<Circuit requirements>*In case of inductive load, install a surge killer.

DP

0V【PNP output circuit 1】

OUT

0V

IN

Control circuit

Withstand voltage: 30V DC
Maximum ON current: 100mA

Internal circuit

DP

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

24V

(Output terminal)

24V
6.8k

0V

Load by external power source

List of Specifications

0V

Internal circuit【NPN output circuit 1】

DN

0V

ASLINKTERMINAL
Manifold Driver

IN

24V

DP

OUT

ASLINKTERMINAL
Relay

Switch,sensor, etc.
(2-wire type)

6.8k

0V

Internal circuit

DN

6.8k

DN

24V
24V

Internal circuit

DP

DP

Load

24V

)

<Circuit requirements>

Control circuit(

IN

Internal circuit

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN) 0V
OFF voltage: 8V or less (between 24V and IN)

6.8k

ASLINKTERMINAL
Small 8-Point Terminal

24V

24V

Internal circuit

DP<Circuit requirements>

Input terminal
Input side of input/output terminalInternal circuit)【PNP input circuit】

24V

24V

Control circuit(

Input terminal
Input side of input/output terminalInternal circuit【NPN input circuit】

ASLINKTERMINAL
Integrated Small Terminal

In case of PNP method

Internal circuitin case of NPN method

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

58

Slave Units (I/O)

ASLINKTERMINAL◆ Small Terminal Block Terminal＜ Outline Dimensional Drawings ＞

Unit: mm

BL296□B-08F□

39.4
28.6
19.5

ASLINKTERMINALASLINKER
SmartLINKER(49)※1
39.4
28.6

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable Type

81
74.5

2-φ3.5

28.9

ASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal

6.5

6.5

*1 State when terminal
block cover is opened

66.62(0.69)ASLINKTERMINAL
Integrated Small Terminal(0.69)ASLINKTERMINAL
Small 8-Point Terminal
32.2

ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications*Example of BL296PB-08F. BL296□B-08F□ also has the same dimensions.

19.5

28.6

BL296□B-08F□-3

39.4

ASLINKTERMINAL

81

39.4
28.6

74.5

28.9

2-φ3.58

8
62.06(1.47)

36(1.47)*Example of BL296PB-08F-3. BL296□B-08F□-3 also has the same dimensions.

Functional icon indication*See page 15 fordetails on function.

59

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Unit: mm

28.6
19.5

BL296□B-08F□-11

39.4

ASLINKTERMINAL

Slave Units (I/O)

ASLINKTERMINALASLINKER
SmartLINKER

81

39.4

74.5

28.6

2-φ3.5ASLINKER
M12/M12 Cable Type

28.9

ASLINKER
M12/M8 Cable Type

8

64.07

(0.18)ASLINKER
Cable Type

8ASLINKER
M12 Connector Type(0.75)ASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal

28.6

ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications*Example of BL296PB-08F-11. BL296□B-08F□-11 also has the same dimensions.

ASLINKTERMINAL

ADP-108 (mounting dedicated DIN rail adaptor) dimensions●Fitted state
95
81

15

15

7

7

15

15

28.9

20.4
7.6
(11.1)

7.5

39.4

8

3.6

(11.1)

8

5.3

35.5

35.5
5.3

7.6

40.8

2-φ3.5

74.5*Example of BL296PB-08F-11. Other models also have the same dimensions as indicated.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

60

Slave Units (I/O)

ASLINKTERMINAL◆ Integrated Small Terminal

Adaptor ADP-T96
ASLINKTERMINAL can be mounted on
the DIN rail using the adaptor.
BL296□B-04F□-4A-20

BL296□B-08F□-4-20

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable Type

Adaptor ADP-W96

ASLINKER
Cable TypeASLINKTERMINAL can be mounted on
the DIN rail using the adaptor.

ASLINKER
M12 Connector Type

BL296□B-16F□-4A-20*Select EP connector (e-CON) from items of accessories.

ASLINKTERMINAL
Small Terminal Block Terminal

ASLINKTERMINAL
Relay＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
shortcircuit

DP/DN
disconnection

24V
drop

Dimension A: 21×80.8×37.7
Dimension B: 21×100×37.1
Dimension C: 43×91×37.1

ID (address)
Duplicate/
Not set／ : Not applicable －: Not determined

ASLINKTERMINAL
Manifold Driver

Number of
I/O points

Input/
outputInput Output specifications

Model

List of Specifications

BL296SB-04F-4A-20

4Consumption
current (mA)
Transmission I/O
side
side

DC input NPN 5

22

DC input PNP 5
DC input /Tr output NPN 5
DC input /2 Tr output PNP 5

22

BL296PB-04F-4A-20

4 Tr output NPN 5

8BL296PB-04FS-4A-20

4 Tr output PNP 5

8
40
40

BL296SB-04FS-4A-20

4BL296XB-04F-4A-20

2BL296XB-04FS-4A-20

2

I/O side
Connection
Connection connector
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON
4-wire type(insulation) e-CON

Dimension(mm)

ASLINKTERMINAL
Small 8-Point Terminal

MethodASLINKTERMINAL
Integrated Small Terminal

Output max.
Input
resistance/ ON current (mA)
Mass 1 point Per 1 Per 1 Response Standard(g)point common
(kΩ)
time
price (￥)

A

35

6.8

Max. 1ms

Open

A

35

6.8

Max. 1ms

Open

A

35

6.8

100

200 Max. 1ms

Open

A

35

6.8

100

200 Max. 1ms

Open

A

35

100

400

Max. 1ms

Open

A

35

100

400 Max. 1ms

Open

B

40

6.8

Max. 1ms

Open

B

40

6.8

Max. 1ms

Open

B

40

6.8

100

400

Max. 1ms

Open

B

40

6.8

100

400 Max. 1ms

Open

B

40

100

800 Max. 1ms

Open

B

40

100

800 Max. 1ms

Open

C

60

6.8

Max. 1ms

Open

C

60

6.8

Max. 1ms

Open

C

60

6.8

100

800 Max. 1ms

Open

C

60

6.8

100

800

Max. 1ms

Open

C

60

100 1600 Max. 1ms

Open

C

60

100 1600 Max. 1ms

Open

ADP-T96

DIN rail adaptor for fitting ASLINKTERMINAL integrated type small 4-point/8-point terminal (4 sets included)

Open

ADP-W96

DIN rail adaptor for fitting ASLINKTERMINAL integrated type small 16-point terminal (4 sets included)

Open

2

BL296SB-08F-4-20

8

DC input NPN 6

BL296SB-08FS-4-20

8BL296XB-08F-4-20

4BL296XB-08FS-4-20

4DC input PNP 6
DC input /4 Tr output NPN 6
DC input /4 Tr output PNP 6

18
18

26
26

BL296PB-08F-4-20

8 Tr output NPN 6 10BL296PB-08FS-4-20

8 Tr output PNP 6 10BL296SB-16F-4A-20

16

DC input NPN 880BL296SB-16FS-4A-20

16

80

BL296XB-16F-4A-20

8BL296XB-16FS-4A-20

8

DC input PNP 8
DC input /8 Tr output NPN 8
DC input /8 Tr output PNP 85050

BL296PB-16F-4A-20

16 Tr output NPN 8 15BL296PB-16FS-4A-20

16 Tr output PNP 8

15*The dimensions are numerical values excluding the cable section.

Power distribution units are available. For details, see page 64.

Functional icon indication*See page 15 fordetails on function.

61

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL＜ LED indication ＞
LED symbol

Indication status

Detailed status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

Transmission signal error

BL296□B-04F□-4A-20
BL296□B-08F□-4-20

LED
indication unit

BL296□B-16F□-4A-20

LED
indication unit

Transmission signal reception

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector Type＜ Circuit diagram ＞

ASLINKTERMINAL
Small Terminal Block Terminal

0V

OUT

0V

0V
4-wire (insulation) type ASLINK terminal(AnyWire based power source)<Circuit requirements>
DN

Load

(Output terminal)

DN<Circuit requirements>
Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

Load

(Output side of input/output terminal)

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

OUT

0V

0V

24V
DP

Control circuit

Internal circuit

24V*In case of inductive load, install a surge killer.

OUT

IN

0V

DN

0V

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

OUT

0V

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detectionIN
0V

Load by external power source

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

Sensing
level
monitoring

24V

0V

Load by external power source

Hi
LO
NG

Load by external power source<Circuit requirements>

OUT

24V

O
F
F

0V

0V

【PNP output circuit 2】

24V

O
N

IN

0V

24V

*See page 15 fordetails on function.

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

Internal circuit

DP

24V

0V

Load by external power source

24V

24V

Control circuit

IN

0V

Functional icon indication

0V

Load

0V

DN

DP

0V

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

DP

24V

Control circuit

Internal circuit

OUT*In case of inductive load, install a surge killer.

OUT

0V

24V

(Output side of input/output terminal)

DN

0V

24V

【NPN output circuit 2】

24V

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA

Load by external power source*In case of inductive load, install a surge killer.

24V

DN

0V

24V

<Circuit requirements>*In case of inductive load, install a surge killer.

DP

0V【PNP output circuit 1】

OUT

0V

IN

Control circuit

Withstand voltage: 30V DC
Maximum ON current: 100mA

Internal circuit

DP

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

24V

(Output terminal)

List of Specifications

24V
6.8k

0V

Load by external power source

ASLINKTERMINAL
Manifold Driver

0V

Internal circuit【NPN output circuit 1】

DN

0V

ASLINKTERMINAL
Relay

IN

Internal circuit

IN

6.8k

24V

DP
Control circuit

Internal circuit

DN

24V
24V

6.8k

DP

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V) 0V
OFF voltage: 8V or less (between IN and 0V)
24V allowable current: Maximum 1A (between 24V and 0V) (per terminal)

Switch,sensor, etc.
(2-wire type)

24V

DP

)

<Circuit requirements>

Load

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN) 0V
OFF voltage: 8V or less (between 24V and IN)
24V allowable current: Maximum 1A (between 24V and 0V) (per terminal)
24V

(

IN

Switch,sensor, etc.
(2-wire type)

Control circuit

6.8k

ASLINKTERMINAL
Small 8-Point Terminal

24V

24V

Internal circuit

DP<Circuit requirements>

Input terminal
Input side of input/output terminalInternal circuit)【PNP input circuit】

24V

24V

Internal circuit(

Input terminal
Input side of input/output terminalInternal circuit【NPN input circuit】

ASLINKTERMINAL
Integrated Small Terminal

In case of PNP method

Internal circuit

In case of NPN method

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

62

Slave Units (I/O)

ASLINKTERMINAL◆ Integrated Small Terminal＜ Outline Dimensional Drawings ＞

Unit: mm

BL296□B-04F□-4Ａ-20

ASLINKTERMINAL■ ADP-T96 (mounting dedicated DIN rail adaptor) dimensions

80.8

14.1

When mounted inparallel to the rail

Part APart APart B

Part B

24.2

10.5

5.25

When mounted
vertically to the rail

20

e-CON compliant 4P socket
Part BUL style 20276
4-core×No.23AWG (Gray) φ4.6

6.9
23Black: DN
Red: DPWhite: 0V
Green: 24V

20
28
37.7

ASLINKTERMINAL
Small Terminal Block Terminal

10.5(18.5)ASLINKER
M12 Connector Type

10.5

21

ASLINKER
Cable Type２-φ3.5

Setting port

6

ASLINKER
M12/M8 Cable TypePart A

5.25
10.5

10.5

ASLINKER
M12/M12 Cable TypeASLINKTERMINAL
Integrated Small Terminal

70.3

5.25

ASLINKER
SmartLINKER

2

（200）

40.8

ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications*Example of BL296SB-04F-4A-20. BL296□B-04F□-4A-20 also has the same dimensions.

ASLINKTERMINAL

BL296□B-08F□-4-20■ ADP-T96 (mounting dedicated DIN rail adaptor) dimensions

21

1

3

3.3

14.1

3

Part A
100

1

When mounted inparallel to the rail

Part APart APart B

Part B

(25)

24.2

Setting port

When mounted
vertically to the rail

（200）

20

6.9

Part B

6.95

5.2

23

Black: DN
Red: DPWhite: 0V
Green: 24V

14.9
21.6

UL style 20276
4-core×No.23AWG (Gray) φ4.6

26.3
37.1

e-CON compliant 4P socket

40.8*Example of BL296SB-08F-4-20. BL296□B-08F□-4-20 also has the same dimensions.

Functional icon indication*See page 15 fordetails on function.

63

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Unit: mm

BL296□B-16F□-4A-20

ASLINKTERMINAL

91
84.5

3.25

11.6
4.5

■ ADP-W96 (mounting dedicated DIN rail adaptor) dimensions

3.25

6.5

6.5

Part A
5.5

41.8
20.9

Setting port
２-φ3.5

19.25

38.5

Slave Units (I/O)

ASLINKTERMINAL

1.5

When mounted
vertically to the rail

When mounted inparallel to the rail

Part B

Part BASLINKER
SmartLINKER

Part APart AASLINKER
M12/M12 Cable Type

53.8

ASLINKER
M12/M8 Cable Type

(21)

6.9

6.5
e-CON compliant 4P socket

ASLINKER
M12 Connector Type

41.6
41.6
26.2
37.1

ASLINKTERMINAL
Integrated Small Terminal

1.5
3

21.6

UL style 20276
4-core×No.23AWG (Gray) φ4.6

ASLINKTERMINAL
Small Terminal Block Terminal

38.7

(57)

Black: DN
Red: DPWhite: 0V
Green: 24V

ASLINKER
Cable TypePart BASLINKTERMINAL
Small 8-Point Terminal（200）

ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications*Example of BL296SB-16F-4A-20. BL296□B-16F□-4A-20 also has the same dimensions.

◆ Power distribution unit

Dimension A: 21×80.8×37.7
Dimension B: 21×100×37.1＜ Specifications ＞／: Not applicable －: Not determined

Dimension(mm)Consumption
current (mA)

Mass
(g)

BL296-04PW4

1

e-CON A

35

Open

BL296-08PW4

1

e-CON B

45

Open

Transmission I/O
side
side

Model

*Select connector fromthe accessory items
when connecting e-CON.

I/O side
Connection
connector

Standard
price (￥)

*The dimensions are numerical values excluding the cable section.

＜ LED indication ＞
LED symbol

Indication status

Detailed status

LINK(Green)On

NormalOffNo power supply

BL296-0□-PW4

LED indication unit

＜ Outline Dimensional Drawings ＞*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

21 3

10.5

10.5

20
28

10.5

Functional icon indication

e-CON compliant 4P socket

5.25

UL style 20276
4-core×No.23AWG (Gray) φ4.6
Black: DN
Red: DPWhite: 0V（200）
Green: 24V

5.25
10.5
２-φ3.5

Setting port

(18.5)

21

6

5.25
10.5

ASLINKTERMINAL

BL296-04PW4

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting1

Sensorcable
disconnection
detection

100

3

3.3

1

Setting port

e-CON compliant 4P socket
UL style 20276
4-core×No.23AWG (Gray) φ4.6
Black: DN
Red: DPWhite: 0V（200）
Green: 24V2

Sensing
level
monitoring

BL296-08PW4

(25)

80.8
70.3

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

14.9
21.6
26.3
37.1

BL296-04PW4

37.7

ASLINKTERMINAL

BL296-08PW4

6.95

5.2

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

64

Slave Units (I/O)

ASLINKTERMINAL◆ Small 8-Point Terminal

Adaptor ADP-96

ASLINKER
SmartLINKER

ASLINKTERMINAL can be mounted on
the DIN rail using the adaptor.

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeASLINKER
Cable Type＜ Specifications ＞

ASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal

O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

ASLINKTERMINAL
Integrated Small Terminal

Dimension A: 17×55×12.7／ : Not applicable －: Not determined

Dimension(mm)

List of Specifications

ID (address)
Duplicate/
Not setOutput max.
Input
resistance/ ON current (mA)
Mass 1 point
Response
Per 1 Per 1
(g)
time
(kΩ)
point common

A

15

6.8

Max. 1ms

Open

A

15

6.8

Max. 1ms

Open

A

15

6.8

100

400 Max. 1ms

Open

A

15

6.8

100

400 Max. 1ms

Open

A

15

100

800 Max. 1ms

Open

A

15

100

800 Max. 1ms

Open

DIN rail adaptor dedicated for fitting ASLINKTERMINAL small 8-point terminal (1 Adaptor for fitting 4 terminals included)

Open

Consumption
current (mA)

Input/
outputInput Output specifications

MethodASLINKTERMINAL
Manifold Driver

24V
drop

Number of
I/O points

BL296SB-08F-20

8DC input

NPN 6 40

BL296SB-08FS-20

8

PNP 6 40

BL296XB-08F-20

4

4

NPN 6 26

BL296XB-08FS-20

4

4

DC input
DC input /Tr output
DC input /Tr output

BL296PB-08F-20

8Tr output

NPN 6

6

BL296PB-08FS-20

8

Tr output

PNP 6

6

ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay

DP/DN
shortcircuit

Model

ADP-96

Transmission
side

I/O
side

PNP 6 26

Connection
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

Standard
price (¥)

*The dimensions are numerical values excluding the cable section.

◆ Connection Cable／ : Not applicable －: Not determined

Minimum
bendingradiusCable length
(mm)

Mass
(g)

BL296-08-CN20R1221.7×215.2×8.6

11

Open

BL296-08-CN50

R1221.7×515.2×8.6

26

Open

BL296-08-CN1K

R1221.7×1015.2×8.6

50

Open

Model

◆ Connection Terminal

Standard
price (¥)

Dimension A: 83×21×28.2／ : Not applicable －: Not determined

Input Output

I/O side
Connection
connector

Dimension(mm)

Number of
I/O points

Mass
(g)

BL296S-08-4

8

e-CON

A

20

Open

BL296X-08-4

4

4

e-CON

A

20

Open

8

e-CON

A

20

Open

JST XH series

A

18

Open

JST XH series

A

18

Open

JST XH series

Model

BL296P-08-4*Select connector from the accessory items
when connecting e-CON.

BL296S-08-9

8

BL296X-08-9

4

BL296P-08-9

Adaptor ADP-T96
ASLINKTERMINAL canbe mounted on the DIN
rail using the adaptor.

4Standard
price (¥)

A

18

Open

BL296S-08-10

8

Molex 5045 series A

18

Open

BL296X-08-10

4

4 Molex 5045 series A

18

Open

8 Molex 5045 series A

18

Open

Connection terminal mounting dedicated
DIN rail adaptor (4 sets included)

Open

8

BL296P-08-10
ADP-T96*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

65

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL◆ Small 8-Point Terminal＜ LED indication ＞
LED symbol

Indication status

Detailed status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

LED
indication unit

BL296□B-08F-20
BL296□B-08FS-20

Transmission signal error
Transmission signal reception

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)Off

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable Type

Input ONASLINKER
M12/M8 Cable Type

Input ONASLINKER
Cable TypeASLINKER
M12 Connector Type＜ Circuit diagram ＞

ASLINKTERMINAL
Small Terminal Block Terminal

0V

OUT

0V

0V
4-wire (insulation) type ASLINK terminal(AnyWire based power source)<Circuit requirements>
DN

Load

(Output terminal)

DN<Circuit requirements>
Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

Load

(Output side of input/output terminal)

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA
DN

OUT

0V

0V

24V
DP

Control circuit

Internal circuit

24V*In case of inductive load, install a surge killer.

OUT

IN

0V

DN

0V

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

OUT

0V

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detectionIN
0V

Load by external power source

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

Sensing
level
monitoring

24V

0V

Load by external power source

Hi
LO
NG

Load by external power source<Circuit requirements>

OUT

24V

O
F
F

0V

0V

【PNP output circuit 2】

24V

O
N

IN

0V

24V

*See page 15 fordetails on function.

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

Internal circuit

DP

24V

0V

Load by external power source

24V

24V

Control circuit

IN

0V

Functional icon indication

0V

Load

0V

DN

DP

0V

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

DP

24V

Control circuit

Internal circuit

OUT*In case of inductive load, install a surge killer.

OUT

0V

24V

(Output side of input/output terminal)

DN

0V

24V

【NPN output circuit 2】

24V

DP

Withstand voltage: 30V DC
Maximum ON current: 100mA

Load by external power source*In case of inductive load, install a surge killer.

24V

DN

0V

24V

<Circuit requirements>*In case of inductive load, install a surge killer.

DP

0V【PNP output circuit 1】

OUT

0V

IN

Control circuit

Withstand voltage: 30V DC
Maximum ON current: 100mA

Internal circuit

DP

OUT

4-wire (insulation) type ASLINK terminal(AnyWire based power source)

24V

24V

(Output terminal)

List of Specifications

24V
6.8k

0V

Load by external power source

ASLINKTERMINAL
Manifold Driver

0V

Internal circuit【NPN output circuit 1】

DN

0V

ASLINKTERMINAL
Relay

IN

Internal circuit

IN

6.8k

24V

DP
Control circuit

Internal circuit

DN

24V
24V

6.8k

DP

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between IN and 0V) 0V
OFF voltage: 8V or less (between IN and 0V)
24V allowable current: Maximum 1A (between 24V and 0V) (per terminal)

Switch,sensor, etc.
(2-wire type)

24V

DP

)

<Circuit requirements>

Load

Rated input voltage: 24V DC
Maximum switching current: 3.5mA
ON current: 2.2mA or more
DN
OFF current: 1mA or lessON voltage: 16V or more (between 24V and IN) 0V
OFF voltage: 8V or less (between 24V and IN)
24V allowable current: Maximum 1A (between 24V and 0V) (per terminal)
24V

(

IN

Switch,sensor, etc.
(2-wire type)

Control circuit

6.8k

ASLINKTERMINAL
Small 8-Point Terminal

24V

24V

Internal circuit

DP<Circuit requirements>

Input terminal
Input side of input/output terminalInternal circuit)【PNP input circuit】

24V

24V

Internal circuit(

Input terminal
Input side of input/output terminalInternal circuit【NPN input circuit】

ASLINKTERMINAL
Integrated Small Terminal

In case of PNP method

Internal circuit

In case of NPN method

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

66

Slave Units (I/O)

ASLINKTERMINAL◆ Small 8-Point Terminal / Connection cable＜ Outline Dimensional Drawings ＞

No.11 poleindication■ADP-96 (mounting dedicated DIN rail adaptor) dimensions

No.12 poleindication

2.2

（200）

Core line coatingouter diameter φ1.4

ASLINKER
M12/M8 Cable Type

12.2

No.1 poleindication

57.2

4-

R1

1

R1

28.6
∅3.5

∅6
1.6
(5.1)

4

No.2 poleindication

1
12

3.5

20.2

55

2.4

ASLINKER
M12/M12 Cable Type

38.4

Black: DN
Red: DPWhite: 0V
Green: 24V

10

ASLINKER
SmartLINKER

UL style 20276
4-core×No.23AWG (Gray) φ4.6

17

R2.3

Unit: mm

BL296□B-08F-20 / BL296□B-08FS-20

ASLINKTERMINAL

9

4.7

5

4.7

＋0
4.5－0.1

7.9

ASLINKER
M12 Connector Type

9

12.7

ASLINKER
Cable Type24

ASLINKTERMINAL
Small 8-Point Terminal

22.3

9.5

Status that mounting dedicated
DIN rail adaptor is fitted andfixed to DIN rail

ASLINKTERMINAL
Integrated Small Terminal

17.5

ASLINKTERMINAL
Small Terminal Block Terminal

Mounting dedicated DIN rail adaptor fitting status

ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications

ASLINKTERMINAL

BL296-08-CN□□

21.7

UL style 20076
No.26AWG (Black) ×12C

Connector manufactured by JST: Housing: ZPDR-12V-S
Contact: SZPD-002T-P0.3

8.6
7.6

BL296-08-CN20 : (200)BL296-08-CN50 : (500)BL296-08-CN1K : (1000)

No.1 poleindication

7.6

No.1 poleindication

Terminal layout (Input)
Pin No. Detail

Functional icon indication*See page 15 fordetails on function.

67

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Line color

Terminal layout (Output)

Terminal layout (Input/output)

Pin No. Detail

Pin No. DetailLine color

Line color

1

24V

Gray

1

24V

Gray

1

24V

Gray

2

24V

Gray/black line2

24V

Gray/black line2

24V

Gray/black line

3

0V

White

3

0V

White

3

0V

White

4

0V

White/black line

40V

White/black line

40V

White/black line

5

IN 0

Black

5

OUT 0

Black

5

IN 0

Black

6

IN 1

Brown

6

OUT 1

Brown

6

IN 1

Brown

7

IN 2

Red

7

OUT 2

Red

7

IN 2

Red

8

IN 3

Orange8

OUT 3

Orange8

IN 3

Orange9

IN 4

Yellow9

OUT 4

Yellow9

OUT 0

Yellow

10

IN 5

Green

10

OUT 5

Green

10

OUT 1

Green

11

IN 6

Blue

11

OUT 6

Blue

11

OUT 2

Blue

12

IN 7

Purple12

OUT 7

Purple12

OUT 3

PurpleReading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL◆ Connection Terminal＜ Outline Dimensional Drawings ＞

Unit: mm

BL296□-08-□

ASLINKTERMINAL

83

(44)

26.3

ASLINKER
SmartLINKER

19.75

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable Type

26.3
38.9

1.4

35

Status that mounting dedicated DIN rail adaptor
is fitted and fixed in a direction the same as the DIN rail

21

13.5

39.4

10.7

43.6

12.7
1

23

R2

28.2

38.9

28.2

■ADP-T96 (mounting dedicated DIN rail adaptor) dimensions

ASLINKER
Cable Type

35

(35)

ASLINKER
M12 Connector Type

24.2

10.7

(27)

Status that mounting dedicated DIN rail adaptor is fitted andfixed in a direction perpendicular to the DIN rail

ASLINKTERMINAL
Small Terminal Block Terminal

19.75

ASLINKTERMINAL
Integrated Small Terminal
BL296□-08-4…(e-CON installed)

BL296□-08-9…(JST XH series installed)
24V
N.C
0V
I/O

Terminallayout0 1 2 30 1 2 34 5 6 7ASLINKTERMINAL
Small 8-Point Terminal

BL296□-08-10…(MOLEX 5045 series installed)

0V
I/O
24V

0V
I/O
24V

4 5 6 70 1 2 3

ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver

4 5 6 7

List of Specifications*This drawing is an example of an e-CON installed product (BL296□-08-4). JST installed product (BL296□-08-9), Molex installed product (BL296□-08-10) also have the same dimensions.

The small 8-point terminal is used in combination of connection terminal andthe customer’s original board with a connection cable.
Space can be further saved if a cus-

Customer’s original board

tomer uniquely develops relay board in

SensorSensorlocations where mechanical systems

SensorSensorare integrated and sensors are condensed. (The ﬁgure is an example of

SensorSensorinput,)

SensorSensorFunctional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Small
8-point
terminal(input)Connection
cable(common)Connection
terminal(input 8 points)

Small
8-point
terminal(output)

Connection
cable(common)Connection
terminal(output
8 points)

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

Connector for I/O
connection sidee・ -CON・JST・MolexConnector for I/O
connection sidee・ -CON・JST・MolexDP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

68

Slave Units (I/O)

ASLINKTERMINAL◆ Relay Terminal (G2R relay mounting type)＜ Outline Dimensional Drawings ＞
ASLINKTERMINAL

Unit: mm

BL296PB-08RS□

6.5

（55）
（40.2）ASLINKER
M12/M8 Cable TypeCan be mounted on the DIN rail

ASLINKER
Cable TypeASLINKER
M12 Connector Type*Example of BL296PB-08RS. BL296PB-08RSN also has the same dimensions.

ASLINKTERMINAL
Small Terminal Block Terminal＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

ASLINKTERMINAL
Relay

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 79×185×55

Model
BL296PB-08RS

8

BL296PB-08RSN

8

Relay output
All points
Relay
independent circuit
Relay not mounted
All points
Relay
independent circuit

Consumption
current (mA)
Transmission
side

I/O
side

6

200

6

*

Connection
4-wire type(insulation)
4-wire type(insulation)

Dimension(mm)

Input/
outputInput Output specifications

Method／ : Not applicable －: Not determined

Number of
I/O points

ASLINKTERMINAL
Manifold Driver
List of Specifications

5

185

ASLINKER
M12/M12 Cable TypeASLINKTERMINAL
Small 8-Point Terminal

4.25

175

ASLINKER
SmartLINKER

ASLINKTERMINAL
Integrated Small Terminal

79

5

4.

φ

2-

32

25.3

8.5

3.5 19.5

Output max.
Input
resistance/ ON current (mA)
Mass 1 point
Response
Per 1 Per 1
(g)
(kΩ)
time
point commonStandard
price (¥)

A 365

3000 3000 Max. 1ms

Open

A 205

3000 3000 Max. 1ms

Open* This differs depending on the relay used.

＜ LED indication ＞
Indication status

LED symbol

Detailed status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

LED
indication unit

BL296PB-08RS□

Transmission signal error
Transmission signal reception

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)
Off

Input ON
Input ON

＜ Circuit diagram ＞
BL296PB-08RS

BL296PB-08RSN<Output circuit><Output circuit>
Output 1 circuit: 3A (max.)
Terminal block: 10A (max.)

24VaModel: OMRON G2R-1-SN
Rated load: 250V AC 10A (Resistance load)DP
30V DC 10A (Resistance load)
250V AC 7.5A (Inductive load)
30V DC 5A (Inductive load)Rated power-on current: 8A
Maximum contact voltage: 380V AC, 125V DC
DN
Maximum contact current: 8A
Maximum opening/closing frequency:
Mechanical 18,000 times/h
Rated load 1,800 times/h
0V
Durability: Mechanical 10 million times or more
Electrical 100 thousand times or more/rated load
(At the above maximum opening/closing frequency)

Internal circuit<Mounting relay>
R*See page 15 fordetails on function.

69

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK SystemaModel: OMRON G2R-1-SN
Rated load: 250V AC 10A (Resistance load)DP
30V DC 10A (Resistance load)
250V AC 7.5A (Inductive load)
30V DC 5A (Inductive load)Rated power-on current: 8A
Maximum contact voltage: 380V AC, 125V DC
DN
Maximum contact current: 8A
Maximum opening/closing frequency:
Mechanical 18,000 times/h
Rated load 1,800 times/h
0V
Durability: Mechanical 10 million times or more
Electrical 100 thousand times or more/rated load
(At the above maximum opening/closing frequency)c*In case of inductive load, install a surge killer.

Functional icon indication

24V<Example of relay fitted>*In case of inductive load, install a surge killer.

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

Internal circuit

Output 1 circuit: 3A (max.)
Terminal block: 10A (max.)※R1c*R1: Relay is not mounted.
G2R-1-SN (with LED indication) etc., is fitted.

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (I/O)

ASLINKTERMINAL◆ Manifold Driver＜ Outline Dimensional Drawings ＞
ASLINKTERMINAL

BL264PB-16F□-T5

20

Manifold manufactured
by CKD Corporation
Compatible with
MN4G-T70-FL series

Unit: mmCan be mounted on the
DIN rail

48.8

ASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeState that terminal isfitted to solenoid
valve manifold of CKD

72

ASLINKER
Cable Type(10)ASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal＜ Specifications ＞
Threshold

O
F
F

DP/DN
disconnection

unnecessary

Minimum value

ASLINKTERMINAL
Integrated Small Terminal

DP/DN
shortcircuit

ID (address)
Duplicate/
Not set24V
drop

Number of
I/O points

Input/
outputInput Output specifications

Model

Consumption
current (mA)
Transmission I/O
side
side

BL264PB-16F-T5

16 Tr output NPN

7

38

BL264PB-16FS-T5

16 Tr output PNP

7

38

Connection
4-wire type(insulation)
4-wire type(insulation)

Dimension A: 72×20×48.8

ASLINKTERMINAL
Small 8-Point Terminal／ : Not applicable －: Not determined

ASLINKTERMINAL
Relay

Dimension(mm)

Interference
countermeasure

Maximum value

Method

Hi
O
N
LO
NG

Output max.
Input
resistance/ ON current (mA)
Mass 1 point
Response
Per 1
Per 1
(g)
(kΩ)
time
point common

A

55

100

Max. 1ms

Open

A

55

100

Max. 1ms

Open

ASLINKTERMINAL
Manifold DriverStandard
price(¥)

List of Specifications＜ LED indication ＞
LED symbol

Indication status

LINK On(Green)Flashing

ALM
(Red)

LINK
ALM

Detailed status

BL264PB-16F□-T5

LED
indication unit

Transmission signal error
Transmission signal reception

Off

No transmission signal

On

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

On
IN
(Orange)
Off

Input ON
Input ON

＜ Circuit diagram ＞

24V

Withstand voltage: 30V DC
Maximum ON current: 100mA

DP

DN

0V

0V

*In case of inductive load, install a surge killer.

*In case of inductive load, install a surge killer.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Coil

DN

<Circuit requirements>

Voltage detection
circuitDP

CoilWithstand voltage: 30V DC
Maximum ON current: 100mA

Voltage detection
circuit

24VInternal circuit<Circuit requirements>

Internal circuit

PNP output circuit

NPN output circuit

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

70

Slave Units (I/O)
ASLINKER
SmartLINKER

ASLINKER /ASLINKTERMINAL＜ List of Specifications ＞○: Mounted

Consumption
Input/
current (mA)outputTransmission I/O
Input Output specifications Method
side
side

Number of
I/O points

Model
B2N87SB-02D-CC20

2

DC input

NPN

3.4

B2N87SB-02DS-CC20

2

DC input

PNP

3.4

BL2LN87SB-02D-CC20

2

DC input

NPN

1.5

10.0

BL2LN87SB-02DS-CC20

2

DC input

PNP

1.5

9.2

BL287SB-02F-2D220

2DC input

NPN

3.4

11.2

BL287SB-02FS-2D220

2DC input

PNP

3.4

11.2

BL287XB-02F-2D220

1

1 DC input / Tr output

NPN

3.5

8.0

BL287XB-02FS-2D220

1

1 DC input / Tr output

PNP

3.6

8.0

BL287PB-02F-2D220

2Tr output

NPN

3.8

4.7

BL287PB-02FS-2D220

2Tr output

PNP

3.8

4.7

BL287SB-02F-2D820

2

DC input

NPN

3.4

11.2

BL287SB-02FS-2D820

2

DC input

PNP

3.4

11.2

BL287XB-02F-2D820

1

1 DC input / Tr output

NPN

3.5

8.0

BL287XB-02FS-2D820

1

1 DC input / Tr output

PNP

3.6

8.0

BL287SB-02F-2D720

2DC input

NPN

3.4

11.2

BL287SB-02FS-2D720

2DC input

PNP

3.4

11.2

BL287XB-02F-2D720

1

1 DC input / Tr output

NPN

3.5

8.0

BL287XB-02FS-2D720

1

1 DC input / Tr output

PNP

3.6

8.0

B281SB-02U-CC20

2

DC input

NPN

15.4

B281SB-02US-CC20

2

DC input

PNP

13.5

B281XB-02U-CC20

1

1 DC input / Tr output

NPN

10.5

B281XB-02US-CC20

1

1 DC input / Tr output

PNP

10.1

B281PB-02U-CC20

2

Tr output

NPN

5.5

ASLINKTERMINAL
Manifold Driver

B281PB-02US-CC20

2

Tr output

PNP

6.5

BL287SB-02F-CC20

2

DC input

NPN

3.4

11.2

List of Specifications

BL287SB-02FS-CC20

2

DC input

PNP

3.4

11.2

BL287XB-02F-CC20

1

1 DC input / Tr output

NPN

3.5

8.0

BL287XB-02FS-CC20

1

1 DC input / Tr output

PNP

3.6

8.0

BL287PB-02F-CC20

2

Tr output

NPN

3.8

4.7

BL287PB-02FS-CC20

2

Tr output

PNP

3.8

4.7

ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay

B280SB-02U-C1220

2

DC input

NPN

15.4

B280SB-02US-C1220

2

DC input

PNP

13.5

B280XB-02U-C1220

1

1 DC input / Tr output

NPN

10.5

B280XB-02US-C1220

1

1 DC input / Tr output

PNP

10.1

B280PB-02U-C1220

2

Tr output

NPN

5.5

B280PB-02US-C1220

2

Tr output

PNP

6.5

×: Not mounted ／: Not applicable － : Not determined

Output max. Sensing Sensor Senor cable
Input
I/O
Interference
ON current (mA)RAS response
resistance/level sensitivity
setting disconnection measure
Per 1
Per 1
time
Connection Mass (g) 1 point(kΩ) point common monitoring read/write detection unnecessary function

2-wire type(non-insulation)
2-wire type(non-insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

20

6.8

×

×

○

×

○

Max. 1ms

20

6.8

×

×

○

×

○

Max. 1ms

20

6.8

×

×

○

×

○

Max. 1ms

20

6.8

×

×

○

×

○

Max. 1ms

45

6.8

×

×

×

×

○

Max. 1ms

45

6.8

×

×

×

×

○

Max. 1ms

45

6.8

100

100

×

×

×

×

○

Max. 1ms

45

6.8

100

100

×

×

×

×

○

Max. 1ms

45

100

200

×

×

×

×

○

Max. 1ms

45

100

200

×

×

×

×

○

Max. 1ms

35

6.8

×

×

×

×

○

Max. 1ms

35

6.8

×

×

×

×

○

Max. 1ms

35

6.8

100

100

×

×

×

×

○

Max. 1ms

35

6.8

100

100

×

×

×

×

○

Max. 1ms

35

6.8

×

×

×

×

○

Max. 1ms

35

6.8

×

×

×

×

○

Max. 1ms

35

6.8

100

100

×

×

×

×

○

Max. 1ms

35

6.8

100

100

×

×

×

×

○

Max. 1ms

15

6.8

×

×

○

×

○

Max. 1ms

15

6.8

×

×

○

×

○

Max. 1ms

15

6.8

100

100

×

×

○

×

○

Max. 1ms

15

6.8

100

100

×

×

○

×

○

Max. 1ms

15

100

100

×

×

○

×

○

Max. 1ms

15

100

100

×

×

○

×

○

Max. 1ms

18

6.8

×

×

×

×

○

Max. 1ms

18

6.8

×

×

×

×

○

Max. 1ms

18

6.8

100

100

×

×

×

×

○

Max. 1ms

18

6.8

100

100

×

×

×

×

○

Max. 1ms

18

100

200

×

×

×

×

○

Max. 1ms

18

100

200

×

×

×

×

○

Max. 1ms

22

6.8

×

×

○*

1

×

○

Max. 1ms

22

6.8

×

×

○*

×

○

Max. 1ms

22

6.8

100

100

×

×

×

×

○

Max. 1ms

22

6.8

100

100

×

×

×

×

○

Max. 1ms

22

100

100

×

×

○*

1

×

○

Max. 1ms

22

100

100

×

×

○*

×

○

Max. 1ms

1

1*1: Impossible to simultaneously
detect at two points

71

Input Output specifications Method

Transmission
side

I/O
side

Connection Mass (g) 1 point(kΩ) point
90

6.8

×

×

×

×

○

Max. 1ms

90

6.8

×

×

×

×

○

Max. 1ms

90

6.8

100

400

×

×

×

×

○

Max. 1ms

90

6.8

100

400

×

×

×

×

○

Max. 1ms

90

100

800

×

×

×

×

○

Max. 1ms

90

100

800

×

×

×

×

○

Max. 1ms

BL296SB-08F-V50

8

DC input

NPN

6

40

BL296SB-08FS-V50

8

DC input

PNP

6

40

BL296XB-08F-V50

44 DC input / Tr output

NPN

6

26

BL296XB-08FS-V50

44 DC input / Tr output

PNP

6

26

BL296PB-08F-V50

8

Tr output

NPN

6

10

BL296PB-08FS-V50

8

Tr output

PNP

6

10

BL296SB-08F-3-V50

8

DC input

NPN

6

40

BL296SB-08FS-3-V50

8

DC input

PNP

6

40

BL296XB-08F-3-V50

4

4 DC input / Tr output

NPN

6

26

BL296XB-08FS-3-V50

4

4 DC input / Tr output

PNP

6

26

BL296PB-08F-3-V50

8

Tr output

NPN

6

10

BL296PB-08FS-3-V50

8

Tr output

PNP

6

10

BL296SB-08F-11-V50

8

DC input

NPN

6

40

BL296SB-08FS-11-V50

8

DC input

PNP

6

40

BL296XB-08F-11-V50

44 DC input / Tr output

NPN

6

26

BL296XB-08FS-11-V50

44 DC input / Tr output

PNP

6

26

BL296PB-08F-11-V50

8

Tr output

NPN

6

10

BL296PB-08FS-11-V50

8

Tr output

PNP

6

10

BL296SB-16F-V50

16

DC input

NPN

8

80

BL296SB-16FS-V50

16

DC input

PNP

8

80

BL296XB-16F-V50

88 DC input / Tr output

NPN

8

50

BL296XB-16FS-V50

88 DC input / Tr output

PNP

8

50

BL296PB-16F-V50

16

Tr output

NPN

8

15

BL296PB-16FS-V50

16

Tr output

PNP

8

15

AnyWireASLINK System

Output max. Sensing Sensor Senor cable
Input
I/O
Interference
ON current (mA)RAS
resistance/level sensitivity
setting disconnection measure function response
Per 1
Per 1
time
monitoring
detection
unnecessarycommonread/write

Consumption
current (mA)

Input/
outputNumber of
I/O points

Model

4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

85

6.8

×

×

×

×

○

Max. 1ms

85

6.8

×

×

×

×

○

Max. 1ms

85

6.8

100

400

×

×

×

×

○

Max. 1ms

85

6.8

100

400

×

×

×

×

○

Max. 1ms

85

100

800

×

×

×

×

○

Max. 1ms

85

100

800

×

×

×

×

○

Max. 1ms

85

6.8

×

×

×

×

○

Max. 1ms

85

6.8

×

×

×

×

○

Max. 1ms

85

6.8

100

400

×

×

×

×

○

Max. 1ms

85

6.8

100

400

×

×

×

×

○

Max. 1ms

85

100

800

×

×

×

×

○

Max. 1ms

85

100

800

×

×

×

×

○

Max. 1ms

150

6.8

×

×

×

×

○

Max. 1ms

150

6.8

×

×

×

×

○

Max. 1ms

150

6.8

100

800

×

×

×

×

○

Max. 1ms

150

6.8

100

800

×

×

×

×

○

Max. 1ms

150

100 1600

×

×

×

×

○

Max. 1ms

150

100 1600

×

×

×

×

○

Max. 1ms

＜ List of Specifications ＞○: Mounted
Consumption
current (mA)

Input/
outputInput Output specifications

Number of
I/O points

Transmission
side

I/O
side

BL296SB-16F-3-V50

16

DC input

NPN

8

80

BL296SB-16FS-3-V50

16

DC input

PNP

8

80

BL296XB-16F-3-V50

88 DC input / Tr output

NPN

8

50

BL296XB-16FS-3-V50

88 DC input / Tr output

PNP

8

50

BL296PB-16F-3-V50

16

Tr output

NPN

8

15

BL296PB-16FS-3-V50

16

Tr output

PNP

8

15

Model

BL296SB-16F-11-V50

16

DC input

NPN

8

80

BL296SB-16FS-11-V50

16

DC input

PNP

8

80

BL296XB-16F-11-V50

8

8 DC input / Tr output

NPN

8

50

BL296XB-16FS-11-V50

8

8 DC input / Tr output

PNP

8

50

BL296PB-16F-11-V50

16

Tr output

NPN

8

15

BL296PB-16FS-11-V50

16

Tr output

PNP

8

15

BL296SB-08F

8

DC input

NPN

6

40

BL296SB-08FS

8

DC input

PNP

6

40

BL296XB-08F

4

4 DC input / Tr output

NPN

6

26

BL296XB-08FS

4

4 DC input / Tr output

PNP

6

26

BL296PB-08F

8

Tr output

NPN

6

10

BL296PB-08FS

8

Tr output

PNP

6

10

BL296SB-08F-3

8

DC input

NPN

6

40

BL296SB-08FS-3

8DC input

PNP

6

40

BL296XB-08F-3

4

4 DC input / Tr output

NPN

6

26

BL296XB-08FS-3

4

4 DC input / Tr output

PNP

6

26

8

Tr output

NPN

6

10

8

Tr output

PNP

6

10

DC input

NPN

6

40

BL296PB-08F-3
BL296PB-08FS-3
BL296SB-08F-11

8BL296SB-08FS-11

8

BL296XB-08F-11

4

4 DC input / Tr output

BL296XB-08FS-11

4

DC input

PNP

6

40

NPN

6

26

4 DC input / Tr output

PNP

6

26

BL296PB-08F-11

8Tr output

NPN

6

10

BL296PB-08FS-11

8

Tr output

PNP

6

10

BL296SB-04F-4A-20

4DC input

NPN

5

22

BL296SB-04FS-4A-20

4DC input

PNP

5

22

BL296XB-04F-4A-20

2

2 DC input / Tr output

NPN

5

18

BL296XB-04FS-4A-20

2

2 DC input / Tr output

PNP

5

18

BL296PB-04F-4A-20

4Tr output

NPN

5

8

BL296PB-04FS-4A-20

4Tr output

PNP

5

8

BL296SB-08F-4-20

8

DC input

NPN

6

40

BL296SB-08FS-4-20

8

DC input

PNP

6

40

BL296XB-08F-4-20

4

4 DC input / Tr output

NPN

6

26

BL296XB-08FS-4-20

4

4 DC input / Tr output

PNP

6

26

BL296PB-08F-4-20

8Tr output

NPN

6

10

BL296PB-08FS-4-20

8Tr output

PNP

6

10

BL296SB-16F-4A-20

16

DC input

NPN

8

80

BL296SB-16FS-4A-20

16

DC input

PNP

8

80

BL296XB-16F-4A-20

8

8 DC input / Tr output

NPN

8

50

BL296XB-16FS-4A-20

8

8 DC input / Tr output

PNP

8

50

BL296PB-16F-4A-20

16

Tr output

NPN

8

15

BL296PB-16FS-4A-20

16

Tr output

PNP

8

15

BL296-04PW4

4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

145

6.8

×

×

×

×

○

Max. 1ms

145

6.8

×

×

×

×

○

Max. 1ms

145

6.8

100

800

×

×

×

×

○

Max. 1ms

145

6.8

100

800

×

×

×

×

○

Max. 1ms

145

100 1600

×

×

×

×

○

Max. 1ms

145

100 1600

×

×

×

×

○

Max. 1ms

140

6.8

×

×

×

×

○

Max. 1ms

140

6.8

×

×

×

×

○

Max. 1ms

140

6.8

100

800

×

×

×

×

○

Max. 1ms

140

6.8

100

800

×

×

×

×

○

Max. 1ms

140

100 1600

×

×

×

×

○

Max. 1ms

140

100 1600

×

×

×

×

○

Max. 1ms

75

6.8

×

×

×

×

○

Max. 1ms

75

6.8

×

×

×

×

○

Max. 1ms

75

6.8

100

400

×

×

×

×

○

Max. 1ms

75

6.8

100

400

×

×

×

×

○

Max. 1ms

75

100

800

×

×

×

×

○

Max. 1ms

75

100

800

×

×

×

×

○

Max. 1ms

70

6.8

×

×

×

×

○

Max. 1ms

70

6.8

×

×

×

×

○

Max. 1ms

70

6.8

100

400

×

×

×

×

○

Max. 1ms

70

6.8

100

400

×

×

×

×

○

Max. 1ms

100

800

×

×

×

×

○

Max. 1ms

100

800

×

×

×

×

○

Max. 1ms

×

×

×

×

○

Max. 1ms

70
70
65

6.8

65

6.8

×

×

×

×

○

Max. 1ms

65

6.8

100

400

×

×

×

×

○

Max. 1ms

65

6.8

100

400

×

×

×

×

○

Max. 1ms

65

100

800

×

×

×

×

○

Max. 1ms

65

100

800

×

×

×

×

○

Max. 1ms

35

6.8

×

×

×

×

○

Max. 1ms

35

6.8

×

×

×

×

○

Max. 1ms

35

6.8

100

200

×

×

×

×

○

Max. 1ms

35

6.8

100

200

×

×

×

×

○

Max. 1ms

35

100

400

×

×

×

×

○

Max. 1ms

35

100

400

×

×

×

×

○

Max. 1ms

40

6.8

×

×

×

×

○

Max. 1ms

40

6.8

×

×

×

×

○

Max. 1ms

40

6.8

100

400

×

×

×

×

○

Max. 1ms

40

6.8

100

400

×

×

×

×

○

Max. 1ms

40

100

800

×

×

×

×

○

Max. 1ms

40

100

800

×

×

×

×

○

Max. 1ms

60

6.8

×

×

×

×

○

Max. 1ms

60

6.8

×

×

×

×

○

Max. 1ms

60

6.8

100

800

×

×

×

×

○

Max. 1ms

60

6.8

100

800

×

×

×

×

○

Max. 1ms

60

100 1600

×

×

×

×

○

Max. 1ms

60

100 1600

×

×

×

×

○

Max. 1ms

×

×

×

×

×

35

1

BL296-08PW4

×: Not mounted ／: Not applicable － : Not determined

Output max. Sensing Sensor Senor cable
Input
I/O
Interference
ON current (mA)RAS response
resistance/level sensitivity
setting disconnection measure
Per 1
Per 1
time
Connection Mass (g) 1 point(kΩ) point common monitoring read/write detection unnecessary function

45

1BL296SB-08F-20

8DC input

NPN

6

40

BL296SB-08FS-20

8

DC input

PNP

6

40

BL296XB-08F-20

4

4 DC input / Tr output

NPN

6

26

BL296XB-08FS-20

44 DC input / Tr output

PNP

6

26

BL296PB-08F-20

8Tr output

NPN

6

6

BL296PB-08FS-20

8

Tr output

PNP

6

6

BL296PB-08RS

8

Relay

6

200

BL296PB-08RSN

8

Relay output All points
independent circuit
Relay output All points
independent circuit

Relay

6

BL264PB-16F-T5

16

Tr output

NPN

7

38

*

BL264PB-16FS-T5

16

Tr output

PNP

7

38

4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)
4-wire type(insulation)

×

×

×

×

×

15

6.8

×

×

×

×

○

Max. 1ms

15

6.8

×

×

×

×

○

Max. 1ms

15

6.8

100

400

×

×

×

×

○

Max. 1ms

15

6.8

100

400

×

×

×

×

○

Max. 1ms

15

100

800

×

×

×

×

○

Max. 1ms

15

100

800

×

×

×

×

○

Max. 1ms

365

3000 3000

×

×

×

×

○

Max. 1ms

205

3000 3000

×

×

×

×

○

Max. 1ms

55

100

×

×

×

×

○

Max. 1ms

55

100

×

×

×

×

○

Max. 1ms

Slave Units (I/O)

ASLINKER /ASLINKTERMINALASLINKER
SmartLINKER
ASLINKER
M12/M12 Cable TypeASLINKER
M12/M8 Cable TypeASLINKER
Cable TypeASLINKER
M12 Connector TypeASLINKTERMINAL
Small Terminal Block Terminal
ASLINKTERMINAL
Integrated Small Terminal
ASLINKTERMINAL
Small 8-Point Terminal
ASLINKTERMINAL
Relay
ASLINKTERMINAL
Manifold Driver
List of Specifications* This differs depending on the relay used.

AnyWireASLINK System

72

73

AnyWireASLINK System

Slave Units (Analog)

Analog (AD/DA) terminals compatible with general-purpose input/output equipment
ASLINKAMP

Analog Input Unit

・・・・・・75

ASLINKAMP

Power Supply Unit for Analog Input ・・・・・・78
ASLINKAMP

Analog Output Unit

・・・・・・79

List of Specifications

・・・・・・83

74

Slave Units (Analog)

ASLINKAMP◆ Analog Input Unit (With 7 segment display, non-insulation type between channels)

Base unit

ASLINKAMP
Analog Input Unit

A state in which the extension unit is added to the base unit

ASLINKAMP
Power Supply Unit for Analog Input(can be mounted on the DIN rail)

ASLINKAMP
Analog Output Unit
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
shortcircuit

DP/DN
disconnection

24V
drop

ID (address)
Duplicate/
Not setDimension A: 10×72×36.7

Model
LA-A12W

16

LB-A12W

16

Type

MethodTransmission
side

I/O
side Connection

Dimension
(mm)
Mass
(g)

／ : Not applicable －: Not determined

Consumption
current (mA)

Number of Input/
I/O points output
Input Output specifications

2-wire type(non-insulation) A 22
2-wire type(non-insulation) A 17

Multi input 0-10V、0-5V、1-5V、 Base 10(switchedby setting) 0-20mA、4-20mA Extension 10

Output max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
price (¥)time(kΩ)
point common
Max. 1ms

Open

Max. 1ms

Open*The dimensions are values excluding the cable section and sensor head section.
* Purchase connectors compatible with the analog side separately.
* The attached line for transmission connection is a 4-core line.
* Analog input of 1 channel for one unit is possible. (16 points are occupied.)＜ Outline Dimensional Drawings ＞

Unit: mm

LA-A12W / LB-A12W
Core line coating outer diameter φ1.1

■ LB-A12W

Transmission cable
UL style 20276
4-core x No.24AWG (gray)φ4.1

Analog port
e-CON (3P)10
70(84.6)(85.9)

32

36.7(41.3)

72

24VL
IN
0VL
10

(4.3)

32

36.7

72

14.3

70

(41.3)（200）

Analog port
e-CON (3P)

24VL
IN
0VL

Black: DN
Red: DPWhite: 0V
Green: 24V(4.3)■LA-A12W

32

ASLINKAMP

32(84.6)(85.9)

10

Functional icon indication*See page 15 fordetails on function.

75

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

10×ｎ■Additional coupling drawing（LA-A12W / LB-A12W）*In order to securely mount to the amplifier,
it is recommended to use a DIN rail stopper.

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (Analog)

ASLINKAMP＜ LED indication ＞
LED symbol

Indication status

Detailed status

On

Transmission signal error

LINK(Green) Flashing

ALM
(Red)
LINK
ALM

Transmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input

On
V(Orange)
Off

When voltage input is set－

ASLINKAMP
Analog Output Unit

On
mA
(Orange)
Off

When current input is set

List of Specifications－＜ Input/output characteristic, resolution ＞
Analog input range
Voltage

Current

Digital output value

Resolution

0-16000

625uV

0-10V
0-5V

312.5uV

1-5V

250uV

0-20ｍA

1250nA

4-20ｍA

1000nA

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

76

Slave Units (Analog)

ASLINKAMP◆ Analog Input Unit (With 7 segment display, insulation type between channels)

Base unit

ASLINKAMP
Analog Input Unit

A state in which the extension unit is added to the base unit

ASLINKAMP
Power Supply Unit for Analog Input(can be mounted on the DIN rail)

ASLINKAMP
Analog Output Unit
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
shortcircuit

DP/DN
disconnection

24V
drop

ID (address)
Duplicate/
Not setDimension A: 10×72×36.7

Model
LA-A1AW

16

LB-A1AW

16

Type

MethodTransmission
side

I/O
side Connection

Dimension
(mm)
Mass
(g)

／ : Not applicable －: Not determined

Consumption
current (mA)

Number of Input/
I/O points output
Input Output specifications

2-wire type(non-insulation) A 22
2-wire type(non-insulation) A 17

Multi input 0-10V、0-5V、1-5V、 Base 20(switchedby setting) 0-20mA、4-20mA Extension 20

Output max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
price (¥)time(kΩ)
point common
Max. 5ms

Open

Max. 5ms

Open*The dimensions are values excluding the cable section and sensor head section.
* Purchase connectors compatible with the analog side separately.
* The attached line for transmission connection is a 4-core line.
* Analog input of 1 channel for one unit is possible. (16 points are occupied.)＜ Outline Dimensional Drawings ＞

Unit: mm

LA-A1AW / LB-A1AW
Core line coating outer diameter φ1.1

■LB-A1AW

Transmission cable
UL style 20276
4-core x No.24AWG (gray)φ4.1

Analog port
e-CON (3P)10
70(84.6)(85.9)

32

36.7(41.3)

72

24VL
IN
0VL
10

(4.3)

32

36.7

72

14.3

70

(41.3)（200）

Analog port
e-CON (3P)

24VL
IN
0VL

Black: DN
Red: DPWhite: 0V
Green: 24V(4.3)■LA-A1AW

32

ASLINKAMP

32(84.6)(85.9)

10

Functional icon indication*See page 15 fordetails on function.

77

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

10×ｎ■Additional coupling drawing（LA-A1AW / LB-A1AW）*In order to securely mount to the amplifier,
it is recommended to use a DIN rail stopper.

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (Analog)

ASLINKAMP＜ LED indication ＞
Indication status

LED symbol

Detailed status

On

Transmission signal error

LINK(Green) Flashing

ALM
(Red)
LINK
ALM

Transmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input

On
V(Orange)
Off

When voltage input is set－

ASLINKAMP
Analog Output Unit

On
mA
(Orange)
Off

When current input is set

List of Specifications－＜ Input/output characteristic, resolution ＞
Analog input range

Digital output value

Resolution

0-16000

625uV

0-10V

Voltage

Current

0-5V

312.5uV

1-5V

250uV

0-20ｍA

1250nA

4-20ｍA

1000nA◆ Power Supply Unit for Analog Input Unit
Used when 24V power supply is required for the analog
output equipment connected to the analog input unit
(only insulation type between channels) shown on page

＜ Outline Dimensional Drawings ＞
ASLINKAMP

Unit: mm

LB-S24at left.

32

Whenconnected tothe master unit

36.7

72

Can be mounted on the DIN rail

＜ Specifications ＞
Type

LB-S2410／: Not applicable －: Not determined

Dimension (mm)ModelPower supply unit 10×72×36.7

70

14.3

Standard
price (￥)

Open

*Thoroughly check the specifications with the Product Guide.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

78

Slave Units (Analog)

ASLINKAMP◆ Analog Output Unit (With 7 segment display, non-insulation type between channels)

Base unit

ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input

A state in which the extension unit is added to the base unit

ASLINKAMP
Analog Output Unit(can be mounted on the DIN rail)

List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
shortcircuit

DP/DN
disconnection

24V
drop

ID (address)
Duplicate/
Not setDimension A: 10×72×36.7

Model

16

LA-DA12W

Current

I/Oside Connection

Dimension
(mm)
Mass
(g)

／ : Not applicable －: Not determined

Consumption
current (mA)

Number of Input/
I/O points output
Input Output specifications

MethodTypeTransmission
side

0-20mA、
4-20mABase

3.18 31.07 (insulation) A 22

4-wire typeOutput max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
price (¥)time(kΩ)
point common

4-wire type16
(insulation) A 13
4-wire type
Base
16
3.18
13.8
0-10V、0-5V、(insulation) A 22
Voltage
4-wire type
1-5V
Extension
16
3.18 13.8 (insulation) A 13

LB-DA12W
LA-DV12W
LB-DV12W

Extension 3.18 31.07

Max. 4ms

Open

Max. 4ms

Open

Max. 4ms

Open

Max. 4ms

Open*The dimensions are values excluding the cable section. * Purchase connectors compatible with the analog side separately.
* Analog output of 1 channel for one unit is possible. (16 points are occupied.)＜ Outline Dimensional Drawings ＞

Unit: mm

LA-D□12W / LB-D□12W
Core line coating outer diameter φ1.1

■ LB-D□12W

Transmission cable
UL style 20276
4-core x No.24AWG (gray)φ4.1

Analog port
e-CON (3P)10
70(84.6)(85.9)

32

36.7(41.3)

72

24V
OUT
0V
10

(4.3)

32

36.7

72

14.3

70

(41.3)（200）

Analog port
e-CON (3P)

24V
OUT
0V

Black: DN
Red: DPWhite: 0V
Green: 24V(4.3)■LA-D□12W

32

ASLINKAMP

32(84.6)(85.9)

10

Functional icon indication*See page 15 fordetails on function.

79

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

10×ｎ■Additional coupling drawing（LA-D□12W / LB-D□12W）*In order to securely mount to the amplifier,
it is recommended to use a DIN rail stopper.

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (Analog)

ASLINKAMP＜ LED indication ＞
LED symbol

Indication status

Detailed status

On

Transmission signal error
Transmission signal and 24V power
supply reception

LINK Flashing(Green)

ALM
(Red)

LINK
ALM

Off

No power supplyOn

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

Normal or no 24 V power supply

Alternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input
ASLINKAMP
Analog Output Unit
List of Specifications＜ Input/output characteristic, resolution ＞
Analog input range
Voltage

Current

Digital output value

Resolution

0-16000

625uV

0-10V
0-5V

312.5uV

1-5V

250uV

0-20ｍA

1250nA

4-20ｍA

1000nA

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

80

Slave Units (Analog)

ASLINKAMP◆ Analog Output Unit (With 7 segment display, insulation type between channels)

Base unit

ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input

A state in which the extension unit is added to the base unit

ASLINKAMP
Analog Output Unit(can be mounted on the DIN rail)

List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
ThresholdDP/DN
disconnection

unnecessary

Minimum value

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 20×72×36.7

Model

16

LA-DA1AW

Current

I/Oside Connection

Dimension
(mm)
Mass
(g)

／ : Not applicable －: Not determined

Consumption
current (mA)

Number of Input/
I/O points output
Input Output specifications

MethodTypeTransmission
side

0-20mA、
4-20mABase

3.18 56.67 (insulation) A 38

4-wire typeOutput max.
Input
resistance/ ON current (mA)
1 point Per 1 Per 1 Response Standard
price (¥)time(kΩ)
point common

4-wire type16
(insulation) A 29
4-wire type
Base
16
3.18
34.02
0-10V、0-5V、(insulation) A 38
Voltage
4-wire type
1-5V
Extension
16
3.18 34.02 (insulation) A 29

LB-DA1AW
LA-DV1AW
LB-DV1AW

Extension 3.18 56.67

Max. 4ms

Open

Max. 4ms

Open

Max. 4ms

Open

Max. 4ms

Open*The dimensions are values excluding the cable section. * Purchase connectors compatible with the analog side separately.
* Analog output of 1 channel per unit is possible (16 points are occupied).

＜ Outline Dimensional Drawings ＞
ASLINKAMP

Unit: mm

LA-D□1AW / LB-D□1AW■LA-D□1AW■ LB-D□1AW
Core line coating outer diameter φ1.1
Transmission cable
UL style 20276
4-core x No.24AWG (gray)φ4.1

Analog port
e-CON (3P)Black: DN
Red: DPWhite: 0V
Green: 24V（200）

Analog port
e-CON (3P)

72

20
70
(84.6)(85.9)

32

36.7(41.3)

32

N/C
OUT
0V
20
24.25

70

(4.3)

N/C
OUT
0V

(4.3)

32

36.7
(41.3)

72

32(84.6)(85.9)

20

Functional icon indication*See page 15 fordetails on function.

81

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

20×ｎ■Additional coupling drawing（LA-D□1AW / LB-D□1AW）*In order to securely mount to the amplifier,
it is recommended to use a DIN rail stopper.

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units (Analog)

ASLINKAMP＜ LED indication ＞
LED symbol

Indication status

Detailed status

On

Transmission signal error
Transmission signal and 24V power
supply reception

LINK Flashing(Green)

ALM
(Red)

LINK
ALM

Off

No power supplyOn

I/O power supply decrease

Flashing

Slave unit voltage decrease

Off

Normal or no 24 V power supply

Alternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set(including disconnection and reverse connection of DP and DN)

LINK
ALM

ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input
ASLINKAMP
Analog Output Unit
List of Specifications＜ Input/output characteristic, resolution ＞
Analog input range
Voltage

Current

Digital output value

Resolution

0-16000

625uV

0-10V
0-5V

312.5uV

1-5V

250uV

0-20ｍA

1250nA

4-20ｍA

1000nA

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

82

Slave Units (Analog)
ASLINKAMP
Analog Input Unit
ASLINKAMP
Power Supply Unit for Analog Input

ASLINKAMP＜ List of Specifications ＞
Model
LA-A12W

16

LB-A12W

16

LA-A1AW

16

LB-A1AW

16

Multi input(Switching by setting) Base
Multi input(Switching by setting) Extension
Multi input(Switching by setting) Base

LA-DA12W

16

LB-DA12W

16

LA-DV12W

16

LB-DV12W

16

LA-DA1AW

16

LB-DA1AW

16

LA-DV1AW

16

LB-DV1AW

16

10
10
20

Multi input(Switching by setting) Extension

20

Base

3.18

ASLINKAMP
Analog Output Unit
List of Specifications

83○: Mounted

Consumption
Input/
Number ofcurrent (mA)I/O points
outputI/OTransmission
Input Output specifications Type side
Connectionside

AnyWireASLINK System

Current
Voltage
Current
Voltage

Extension 3.18
Base

3.18

Extension 3.18
Base

3.18

Extension 3.18
Base

3.18

Extension 3.18

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
4-wire type
線式（絶縁）
31.07 4(insulation)
4-wire type31.07 (insulation)
4-wire type13.8
(insulation)
4-wire type13.8
(insulation)
4-wire type
線式（絶縁）
56.67 4(insulation)
4-wire type56.67 (insulation)
4-wire type34.02 (insulation)
4-wire type34.02 (insulation)

Mass(g)

×: Not mounted ／: Not applicable － : Not determined

Output max. Sensing Sensor Senor cable Interference
Input
I/O
resistance/ ON current (mA)level sensitivity
RAS response
1 point Per 1
setting disconnection measure
Per 1
time
(kΩ)
point common monitoring read/write detection unnecessary function

22○

Max. 5ms

17○

Max. 5ms

22○

Max. 5ms

17○

Max. 5ms

22○

Max. 4ms

13○

Max. 4ms

22○

Max. 4ms

13○

Max. 4ms

38○

Max. 4ms

29○

Max. 4ms

38○

Max. 4ms

29○

Max. 4ms

AnyWireASLINK System

84

85

AnyWireASLINK System

Slave Units(Sensor/Amplifier)Diagnosis of sensors/amplifiers directly coupled to
Sho-Haisen network
ASLINKSENSOR

Photoelectric TypeASLINKSENSOR

Laser TypeASLINKAMP

Fiber TypeASLINKSENSOR

Proximity TypeASLINKSENSOR

Pressure TypeASLINKSENSOR

Cylinder TypeASLINKSENSOR

Photo Interrupter TypeASLINKMONITOR

Line Monitor
ASLINKMONITOR

・・・・・・89
・・・・・ 101
・・・・・ 105
・・・・・ 113
・・・・・ 147
・・・・・ 149
・・・・・ 151
・・・・・ 152

Small Display Unit

・・・・・ 152

List of Specifications

・・・・・ 153

86

Type of AMP

Photoelectric Type
Laser TypeFiber Type
Detection ofpresence/absence of workby light such as visible light

Input/output specifications

Transmission

LED light
sourceRecurrent
reflection

Amplifier built-in

Spreadreflection

Laser lightsourceAmplifier-separated

87

AnyWireASLINK System

Transmission
Recurrent
reflection

LED light sourceDetection distanceProtective
Appearance
structure

Model

Sensing
SensorInterference
level
sensitivity setting measuremonitoring
read/write
unnecessary
O
N
O
F
F

Hi
LO
NG

Maximum value
ThresholdMinimum value

Interference
countermeasureunnecessary

RAS
function
RAS
function

BS-H0117-PC-SET
IP67
5000mm

BS-H0117-PC12-SET
IP67
company standard
oil resistance*1

BS-H0117G-PC-SET
BS-H0217-1K

IP67

IP67
company standard
oil resistance*1

BS-H0217G-1K
BS-H0317-1K

IP67

0.3 ～ 10m

Depending on fiber head

○

○

○

BS-H0317-3012

500mm

30m

○

BS-H0217-3012

3000mmIP67
company standard
oil resistance*1

BS-H0317G-1K

IP67

BS-L0117-PC-SET

IP67

BS-L0217-1K

IP40

L□-F1011

IP66

BA-F116-□□―

B289SB-01AF-CA□□□-V○* Withlimitation○*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

AnyWireASLINK System

88

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆ Photoelectric transmission type (IP67, IP67 company standard oil resistance*1)

Photoelectric Type
Laser TypeFiber Type

BS-H0117-PC-SET (Cable)

BS-H0117G-PC-SET (Cable)

Proximity Type
Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

BS-H0117-PC12-SET*Contact our sales division
for attachment fittings.

(Cable with M12 connector)＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 11×20×33

Model

Transmission light

1 emitting (red light)

Set model
BS-H0117-PC-SET

1Transmission light IP67 5000

receiving (red light)
Transmission light1

Set model
BS-H0117G-PC-SET

1

10
10

1 emitting (red light)

Set model
BS-H0117-PC12-SET

10Transmission light IP67 5000
10
receiving (red light)
Transmission light IP67
10
1 emitting (red light) company
Transmission light standard*1 5000
10
receiving (red light) oil resistanceDimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Consumption
Input/
Detection
outputType distance current (mA) Connection
ssion I/O
Input Output specifications(mm) Transmi
side
side
Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

Minimum
detected object

Response Standard
time
price (￥)A 33 Opaque body of φ12mm Max. 2 cycle times

Open

A 33 Opaque body of φ12mm Max. 2 cycle times
A 22 Opaque body of φ12mm Max. 2 cycle times

Open

A 22 Opaque body of φ12mm Max. 2 cycle times
A 33 Opaque body of φ12mm Max. 2 cycle times

Open

A 33 Opaque body of φ12mm Max. 2 cycle times* The dimensions are numerical values excluding the cable section.
* “BS-H0117-PC-SET” is a combination of photoelectric (transmission light emitting) “BS-H0117-1KP” and photoelectric (transmission light receiving) “BS-H0117-1KC.”* “BS-H0117-PC12-SET” is a combination of photoelectric (transmission light emitting) “BS-H0117-30P12” and photoelectric (transmission light receiving) “BS-H0117-30C12.”* “BS-H0117G-PC-SET” is a combination of photoelectric (transmission light emitting) “BS-H0117G-1KP” and photoelectric (transmission light receiving) “BS-H0117G-1KC.”*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

89

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units(Sensor/Amplifier)

ASLINKSENSOR＜ LED indication ＞
LEDsymbolIndication status

LINK
ALM

BS-H0117-PC-SET
BS-H0117-PC12-SET
BS-H0117G-PC-SET

On

Transmission signal error

Off

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease* 1* 2

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK(Green) Flashing

ALM
(Red)

Detailed status

Transmission signal reception(including disconnection and

LINK
ALM

On
IN
(Orange)Off

LED indication unit

Photoelectric Type
Laser Type

Input ON

Fiber Type

Input OFF

Proximity Type

*1 When alarm diagnosis function is enabled*2 Not available on the transmission light emitting side

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor＜ Characteristic diagram ＞ (Reference value)・Parallel displacement characteristic

Small Display Unit

・Distance characteristic

List of Specifications

1000

100
0

2

4

AD value–Y (Digit)

Parallel displacement distance–Y (mm)

1200
200

6

-100

800
600
400
200

-200

0
Set distance–X (m)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting024Distance–X (m)Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

6

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System90◆ Photoelectric transmission type (IP67, IP67 company standard oil resistance*1)＜ Outline Dimensional Drawings ＞
ASLINKSENSOR

Unit: mm

BS-H0117-PC-SET
20Light emitting
and receiving surface

11

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port

17

（2）

Photoelectric Type

Indication
unit

Laser Type

Proximity Type

25.4

31

Fiber Type

Pressure Type
Cylinder Type(100

Photo Interrupter Type

0)

2-M3
(through)

Line Monitor
UL style 2103
2-core×No.24AWG (Black) φ4.1

Small Display Unit
List of Specifications

Core line coatingouter diameter φ1.5

ASLINKSENSOR

Red: DPBlack: DN

BS-H0117-PC12-SET

Setting port

Indication unit
20
17

25.4

31

（2）

11

Transmission cable
UL style 2103 105˚
2-core×24AWG (Black) φ4.1

Lightemitting
andreceivingsurface2-M3(through)

44.7
2
φ14.9

1

3

（300）
XS5H (plug)

Functional icon indication*See page 15 fordetails on function.

91

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

4
1 N/C
2 DP
3 N/C
4 DN

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Unit: mm

BS-H0117G-PC-SETASLINKSENSOR

11

20

17

(2)

Indication
unit

Setting port

Photoelectric Type
Laser Type

31

25.4

Fiber Type
Proximity Type

Light emitting
andreceivingsurface

Pressure Type（

Cylinder Type

10
00
）

2-M3
(through)

Photo Interrupter TypeLine Monitor

UL style 2103
2-core×No.24AWG (Black) φ4.1

Small Display Unit

Core line coatingouter diameter φ1.5

Red: DPBlack: DN

List of Specifications*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

92

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Photoelectric recurrent reflection type
(IP67, IP67 company standard oil resistance*1)

Photoelectric Type
Laser TypeFiber Type

BS-H0217-1K (Cable)

BS-H0217G-1K (Cable)

Proximity Type
Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

BS-H0217-3012*Contact our sales division
for attachment fittings.

(Cable with M12 connector)＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 11×20×33

Model
BS-H0217-1K

1

BS-H0217-3012

1

BS-H0217G-1K

1Recurrent reflection
IP67 3000 10(red light)
Recurrent reflection
IP67 3000 10(red light)
IP67
Recurrent reflection companystandard
10(red light)
oil resistance*1 3000

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Consumption
Input/
Detection
outputType distance current (mA) Connection
ssion I/O
Input Output specifications(mm) Transmi
side
side
Number of
I/O points

Minimum
detected object

Response Standard
time
price (￥)

2-wire type(non-insulation) A 33 Opaque body of φ12mm Max. 2 cycle times
2-wire type(non-insulation) A 22 Opaque body of φ12mm Max. 2 cycle times
2-wire type(non-insulation) A 33 Opaque body of φ12mm Max. 2 cycle times

Open
Open
Open

*The dimensions are numerical values excluding the cable section.

*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

◆Option・Reflection plate for photoelectric sensor／: Not applicable －: Not determined

Model

AKR-2

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Dimensions (mm)AKR-1

Reflection plate

60.9×50.9

Open

AKR-2

Reflection plate

42×35

Open

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

93

AnyWireASLINK System

Standard
price (￥)

Type

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units(Sensor/Amplifier)

ASLINKSENSOR＜ LED indication ＞
LEDsymbolIndication status

Detailed status
Transmission signal error

Off

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease* 1

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-H0217-1K
BS-H0217-3012
BS-H0217G-1K

OnTransmission signal reception(including disconnection and

LINK
ALM

On
IN
(Orange)Off

LED indication unit

Photoelectric Type
Laser Type

Input ON

Fiber Type

Input OFF

Proximity Type

*1: When alarm diagnosis function is enabled

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor＜ Characteristic diagram ＞ (Reference value)

150

1200

100

1000

50

800

0

1

2

3

-50
-100
-150

Small Display Unit

・Distance characteristic

AD value–Y (Digit)

Parallel displacement distance–Y (mm)・Parallel displacement characteristic

List of Specifications

600
400
200

AKR-1

0

AKR-2

0

1

2
AKR-1

Set distance–X (m)

3
AKR-2

Distance–X (m)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

94

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Photoelectric recurrent reflection type (IP67, IP67 company standard oil resistance*1)＜ Outline Dimensional Drawings ＞
ASLINKSENSOR

Unit: mm

BS-H0217-1K
20

11Light emitting andreceiving surface

Setting port

17

（2）

Photoelectric Type

Indication
unit

Laser Type

Proximity Type

25.4

31

Fiber Type

Pressure Type
Cylinder Type(100

Photo Interrupter Type

0)

2-M3
(through)

Line Monitor
UL style 2103
2-core×No.24AWG (Black) φ4.1

Small Display Unit
List of Specifications

Core line coatingouter diameter φ1.5

ASLINKSENSOR

Red: DPBlack: DN

BS-H0217-3012

Setting port

Indication unit
20
17

25.4

31

（2）

11

Transmission cable
UL style 2103 105˚
2-core×24AWG (Black) φ4.1

Lightemitting
andreceivingsurface2-M3(through)

44.7
2
φ14.9

1

3

（300）
XS5H (plug)

Functional icon indication*See page 15 fordetails on function.

95

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

4
1 N/C
2 DP
3 N/C
4 DN

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Unit: mm

BS-H0217G-1K

ASLINKSENSOR

11

20

17

(2)

Indication
unit

Setting port

Photoelectric Type
Laser Type

31

25.4

Fiber Type
Proximity Type

Light emitting
andreceivingsurface

Pressure Type（

Cylinder Type

10
00
）

2-M3
(through)

Photo Interrupter TypeLine Monitor

UL style 2103
2-core×No.24AWG (Black) φ4.1

Small Display Unit

Core line coatingouter diameter φ1.5

Red: DPBlack: DN

List of Specifications*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

96

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Photoelectric spread reflection type
(IP67, IP67 company standard oil resistance*1)

Photoelectric Type
Laser TypeFiber Type

BS-H0317-1K (Cable)

BS-H0317G-1K (Cable)

Proximity Type
Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

BS-H0317-3012*Contact our sales division
for attachment fittings.

(Cable with M12 connector)＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 11×20×33

Model
BS-H0317-1K

1

BS-H0317-3012

1

BS-H0317G-1K

1

Spread reflection
IP67 500(red light)
Spread reflection
IP67 500(red light)
Spread reflection companystandard
IP67
500(red light)
oil resistance*1

10
10
10

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Consumption
Input/
Detection
outputType distance current (mA) Connection
ssion I/O
Input Output specifications(mm) Transmi
side
side
Number of
I/O points

Output max.
Input
resistance/ ON current (mA) Response Standard
1 point Per 1
Per 1
time
price (￥)(kΩ)
point common

2-wire type(non-insulation) A 33
2-wire type(non-insulation) A 22
2-wire type(non-insulation) A 33

Max. 2 cycle times

Open

Max. 2 cycle times

Open

Max. 2 cycle times

Open*The dimensions are numerical values excluding the cable section.

*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

97

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units(Sensor/Amplifier)

ASLINKSENSOR＜ LED indication ＞
LEDsymbolIndication status

Detailed status
Transmission signal error

Off

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease* 1

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-H0317-1K
BS-H0317-3012
BS-H0317G-1K

OnTransmission signal reception(including disconnection and

LINK
ALM

On
IN
(Orange)Off

LED indication unit

Photoelectric Type
Laser Type

Input ON

Fiber Type

Input OFF

Proximity Type

*1: When alarm diagnosis function is enabled

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor＜ Characteristic diagram ＞ (Reference value)・Parallel displacement characteristic

Small Display Unit

・Distance characteristic

List of Specifications

1000

10

AD value–Y (Digit)

Parallel displacement distance–Y (mm)

1200
20

0
200

400

600

-10

800
600
400
200

-20

0
Set distance–X (mm)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

0200
400Distance–X (mm)Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

600

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System98◆Photoelectric spread reflection type (IP67, IP67 company standard oil resistance*1)＜ Outline Dimensional Drawings ＞
ASLINKSENSOR

Unit: mm

BS-H0317-1K
20Light emitting andreceiving surface

11

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port

17

（2）

Photoelectric Type

Indication
unit

Laser Type

Proximity Type

25.4

31

Fiber Type

Pressure Type
Cylinder Type(100

Photo Interrupter Type

0)

2-M3
(through)

Line Monitor
UL style 2103
2-core×No.24AWG (Black) φ4.1

Small Display Unit
List of Specifications

Core line coatingouter diameter φ1.5

ASLINKSENSOR

Red: DPBlack: DN

BS-H0317-3012

Setting port

Indication unit
20
17

25.4

31

（2）

11

Transmission cable
UL style 2103 105˚
2-core×24AWG (Black) φ4.1

Lightemitting
andreceivingsurface2-M3(through)

44.7
2
φ14.9

1

3

（300）
XS5H (plug)

Functional icon indication*See page 15 fordetails on function.

99

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

4
1 N/C
2 DP
3 N/C
4 DN

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

＜ Outline Dimensional Drawings ＞

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Unit: mm

BS-H0317G-1K

ASLINKSENSOR

11

20

17

(2)

Indication
unit

Setting port

Photoelectric Type
Laser Type

31

25.4

Fiber Type
Proximity Type

Light emitting
andreceivingsurface

Pressure Type（

Cylinder Type

10
00
）

2-M3
(through)

Photo
Interrupter Type
フォトインタラプタタイプ
Line Monitor

UL style 2103
2-core×No.24AWG (Black) φ4.1

Small Display Unit

Core line coatingouter diameter φ1.5

Red: DPBlack: DN

List of Specifications*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

100

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Laser spot transmission type (IP67)
Recurrent reflection type (IP67)

Photoelectric Type
Laser TypeFiber Type
Proximity Type
Pressure Type

BS-L0117-PC-SET

Cylinder Type

BS-L0217-1K

Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications*Contact our sales division
for attachment fittings.

＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 11×20×33／: Not applicable －: Not determined

Consumption
Input/
Detection
outputType distance current (mA) Connection
ssion I/O
Input Output specifications(m) Transmi
side
side
Number of
I/O points

Model

1

Set model
BS-L0117-PC-SET

1

BS-L0217-1K

1Transmission
light emitting(red LD)
Transmission
light receiving(red LD)
Recurrent
reflection(red LD)

Laser
spot
IP67

30

Dimension
(mm)
Mass
(g)

* With limitation

Output max.
Input
resistance/ ON current (mA) Response Standard
1 point Per 1
Per 1
time
price (￥)(kΩ)
point common

2-wire type(non-insulation) A 33
2-wire type(non-insulation) A 33
2-wire type(non-insulation) A 33

78

0.3 ～ 10 10Max. 2 cycle times

Open

Max. 2 cycle times
Max. 2 cycle times

Open* The dimensions are numerical values excluding the cable section.
* “BS-L0117-PC-SET” is a combination of transmission light emitting “BS-L0117-1KP” and transmission light receiving “BS-L0117-1KC.”* The detection distance by “BS-L0217-1K” is the value when using “AKR-1.”◆Option・Reflection plate for photoelectric sensor／: Not applicable －: Not determined

Model

AKR-2

Functional icon indication*See page 15 fordetails on function.

101

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Dimensions (mm)AKR-1

Reflection plate

60.9×50.9

Open

AKR-2

Reflection plate

42×35

Open

Interference Interference
countermeasure countermeasureunnecessaryStandard
price (￥)

Typefor transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR＜ LED indication ＞
LEDsymbolIndication status

Detailed status
Transmission signal error

Off

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease* 1* 2

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-Ｌ0117-1KP
BS-Ｌ0117-1KC
BS-Ｌ0217-1K

On

Transmission signal reception(including disconnection and

LINK
ALM
ALM

IN*2/
On
Opticalaxis check Off
indication(Orange) Flashing

LED indication unit

Photoelectric Type
Laser Type

Input ON

Fiber Type

Input OFF

Proximity Type

Unstable operation area

Pressure Type

*1 When alarm diagnosis function is enabled*2 Not available on the transmission light emitting side

Cylinder Type＜ Characteristic diagram ＞ (Reference value)

Photo Interrupter Type

◆BS-L0117-PC-SETLine Monitor

・Distance characteristic

40.0

0.0
0

10

20

30

40

-20.0

Spot diameter–Y (mm)

20.0

800
600
400

Small Display Unit
List of Specifications

30

1000

20

10

200
-40.0
0

0

10

20

Distance–X (m)◆BS-L0217-1K

10

20Distance–X (m)

30

10.0

800

5

10

15

-10.0

400
200

-30.0

0

O
F
F

Hi
LO
NG

Sensing
level
monitoring

0

5

10

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

10

5

0

15

Distance–X (m)Distance–X (m)

O
N

15

600

-20.0

Functional icon indication

・Distance-spot diameter characteristic

Spot diameter–Y (mm)1000
AD value–Y (Digit)

20.0*See page 15 fordetails on function.

0・Distance characteristic
1200

0

40

* Data measured using “AKR-1”

30.0

0.0

30

Distance–X (m)・Parallel displacement characteristic
Parallel displacement distance–Y (mm)・Distance-spot diameter characteristic

1200

AD value–Y (Digit)

Parallel displacement distance–Y (mm)・Parallel displacement characteristic

Transmission

DP/DN line
disconnection disconnection
detection

0

5

DP/DN
shortcircuit

10
Distance–X (m)Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

15

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System102◆Laser spot transmission type (IP67)＜ Outline Dimensional Drawings ＞
ASLINKSENSOR

Unit: mm

BS-L0117-PC-SET

20

11Slave Units(Sensor/Amplifier)

ASLINKSENSOR

17

Indication
unit

Setting port

2

Photoelectric Type

31

Light
receiving center

Proximity Type

25.4

Fiber Type

6

Laser TypeLight
emitting center

Pressure Type

）
00
10

（

Cylinder Type
2-M3
(through)

Photo Interrupter TypeLine Monitor

UL style 2103 105˚
2-core×24AWG (Red Black) φ4.1 Black

Small Display Unit
List of Specifications

Red: DPBlack: DNCore line coatingouter diameter φ1.5

Functional icon indication*See page 15 fordetails on function.

103

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Laser spot recurrent reflection type (IP67)＜ Outline Dimensional Drawings ＞

Unit: mm

BS-L0217-1K

ASLINKSENSOR

11

20

17

Indication
unit

Setting port

2

Photoelectric TypeLight
emitting center

Fiber Type

25.4

31

Light
receiving center

6

Laser Type

Proximity Type
Pressure Type（

Cylinder Type

）
00
10

2-M3
(through)

Photo Interrupter TypeLine Monitor

UL style 2103 105˚
2-core×24AWG (Red Black) φ4.1 Black

Small Display Unit

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

List of Specifications

Red: DPBlack: DNCore line coatingouter diameter φ1.5

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

104

Slave Units(Sensor/Amplifier)

ASLINKAMP◆Fiber type (With 7 segment display)

Base unit

Photoelectric Type
Laser TypeA state in which the extension unit isadded to the base unit
(Can be mounted on the DIN rail)
Up to 32 units (including a base unit)
can be additionally coupled.

Fiber Type
Proximity Type

Cylinder Type
Photo Interrupter Type＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
ThresholdDP/DN
disconnection

unnecessary

Minimum value

24V
drop

ID (address)
Duplicate/
Not setDimension A: 10×72×36.7／: Not applicable －: Not determinedLine Monitor

Number of
I/O points

Small Display Unit
List of Specifications

DP/DN
shortcircuit

Model

Input/
outputspecifications

Input Output

TypeConsumption
current (mA) Connection

Transmission I/O
side
side

LA-F1011

1

Fiber head (red light) Base 1.9

LB-F1011

1

Fiber head (red light) Extension 1.9

Dimension
(mm)
Mass
(g)

Pressure Type

Output max.
Input
resistance/ ON current (mA) Response Standard
1 point Per 1
Per 1
time
price (￥)(kΩ)
point common

4-wire type

25 (insulation) A 21
4-wire type
25 (insulation) A 17

Max. 2 cycle times

Open

Max. 2 cycle times

Open*The dimensions are values excluding the cable section and sensor head section.
*Do not use a head which uses a fiber in which the number of cores is 217 or more.

＜ Outline Dimensional Drawings ＞
ASLINKAMP

Unit: mm

LA-F1011 / LB-F1011■LA-F1011■LB-F1011

Core line coating outer diameter φ1.1
Transmission cable
UL style 20276
4-core x No.24AWG (gray)φ4.1

Black: DN
Red: DPWhite: 0V
Green: 24V

（200）

72

72

32

32

36.7
(41.3)

2-φ2.236.7(41.3)

2-φ2.270(84.6)(85.9)

32

10
14.3

(4.3)

10

70

(4.3)

LB-F1011

LA-F1011

32(84.6)(85.9)

10

Functional icon indication*See page 15 fordetails on function.

105

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

10×ｎ■Additional coupling drawing（LA-F1011 / LB-F1011）

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

A state in which the extension unit is added to the base unit
Up to 32 units (including a base unit) can be additionally coupled.
*In order to securely mount to the unit,
it is recommended to use a DIN rail stopper.

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKAMP＜ LED indication ＞
LEDsymbolIndication status

Detailed status

On

LA-F1011
LB-F1011

Transmission signal error

LINK(Green) Flashing

LED indication unit

Normal (transmission signal, 24V power are supplied)Off

No 24V powerOn

Sensing level decrease*
IO power reduction(turns off when without 24V power)

ALM
(Red)

Slave unit voltage decrease

Flashing

LINK
ALM(including disconnection and reverse connection of DP and DN)

OffNormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

On
IN
(Orange)
Off

Photoelectric Type
Laser TypeFiber Type

Input ON

Proximity Typenput OFF

Pressure Type

*When alarm diagnosis function is enabled
Cylinder Type
Photo Interrupter Type＜ Characteristic diagram ＞ (Reference value)・Parallel displacement characteristic150

・Distance characteristic

Digital value–Y (Digit)

Distance–Y (mm)Small Display Unit
List of Specifications

4000

100
50
0

Line Monitor

20

40

100 200 240 300 400 500

-50

2000

1000

Ｙ

-100

3000

Ｘ

-150

AFT-1

AFT-1-1

AFT-2

0

AFT-4

30

50

AFT-1

Distance–X (mm)95

150 250 350 450 550 650

AFT-1-1

AFT-2

AFT-4

Distance–X (mm)◆Option・Fiber head

Example of use

Light emitting/receiving set
with one fiber cutter

Application

Core
Cable Detection distance (mm)Cable
Bending diameter specification length Without 7 segment With 7 segment Standard
radiusprice (￥)
With
No
With
No
(mm)
(mm) diagnosis(mm)
diagnosis diagnosis diagnosis
General- Transmission
Singlecore
Top view Screw type M4
purpose2000 480 820 410 600
R30 φ2.2
Open
type
φ1.0
General- Transmission
Singlecore
Top view Screw type M3
purposeOpen
2000 210 340 160 210
R20 φ1.0
type
φ0.5
General- Transmission
Single core
Top
view
Screw
type
M3
purpose
2000
R25
φ1.0
Open
490
300
800
420
type
φ0.75
General- Transmission
Screw type M3
Singlecore
Top view (Heat resistance 100ºC) R20 φ1.0
purposeOpen
2000 260 430 170 240
type
φ0.5
*With diagnosis: When sensing level monitoring function (O-100 mode) is used / Without diagnosis: When using only with ON/OFF*Light emitting and receiving set, respectively free cut. *Mounting bracket not included.
*Contact our sales division for corresponding heads other than the above.

Model

AFT-4
AFT-1
AFT-2
AFT-1-1

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Detection View
method direction

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
settingType

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

106

Slave Units(Sensor/Amplifier)

ASLINKAMP◆Fiber type (IP66)

Photoelectric Type
Laser Type

BA-F116-12
Cable with M12 connector

Fiber Type
Proximity Type

Cylinder Type
Photo Interrupter TypeCan be mounted on the DIN rail

＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

24V
drop

ID (address)
Duplicate/
Not setDimension A: 13×72.8×38.3／: Not applicable －: Not determinedLine Monitor

Number of
I/O points

Small Display Unit
List of Specifications

DP/DN
shortcircuit

Model

Input/
outputspecifications

Input Output

TypeConsumption
current (mA) Connection

Transmission I/O
side
side

BA-F116-12

1

Fiber head (red light) Base 11

BA-F1161

Fiber head (red light) Base 11

Dimension
(mm)
Mass
(g)

Pressure Type

BA-F1162-core cable

Output max.
Input
resistance/ ON current (mA) Response Standard
1 point Per 1
Per 1
time
price (￥)(kΩ)
point common

2-wire type(non-insulation) A 40
2-wire type(non-insulation) A 47

Max. 2 cycle times

Open

Max. 2 cycle times

Open*The dimensions are values excluding the cable section and sensor head section.
*Do not use a head which uses a fiber in which the number of cores is 217 or more.

＜ Outline Dimensional Drawings ＞
ASLINKAMP

Unit: mm

BA-F116-12 / BA-F116■BA-F116

3：N/C

4：DN

（4.5）

27.2

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

9.6

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

107

AnyWireASLINK System

Core wire coating outer
diameter φ1.5

（96.4）

27.2（131.8）Maximum value

DN (Black)
DP (Red)

38.3
3

11 7
13

60.3
63.2

9.6

Functional icon indication

UL style 2103
2-core×No.24AWG (Black) φ4.1

2-φ2.2

121

11 7
13

（1000）

M12 waterproof connector (plug)

38.3
32-φ2.2*See page 15 fordetails on function.

1：N/C（96.4）

UL style 2103
2-core×No.24AWG (Black) φ4.1

2：DP

（4.5）

（300）

121

■BA-F116-12

60.3
63.2
（131.8）Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units(Sensor/Amplifier)

ASLINKAMP＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BA-F116-12
BA-F116

Transmission signal error

OnLED
indication unit

Transmission signal reception

Off(including disconnection and
No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

On
IN
(Orange)
Off

Photoelectric Type
Laser Type

Input ON

Fiber Type

Input OFF

Proximity Type

*When alarm diagnosis function is enabled

Pressure Type
Cylinder Type
Photo Interrupter Type＜ Characteristic diagram ＞ (Reference value)・Parallel displacement characteristic

Line Monitor

・Distance characteristic

Small Display Unit

1000

List of Specifications

200
100
0

50

Digital value–Y (Digit)

Distance–Y (mm)800

150 250 340 400 500 700 820

-100

600

400

200
-200
AFT-1

AFT-1-1

AFT-2

0

AFT-4

50

140

AFT-1

Distance–X (mm)

260

360

600

AFT-1-1
AFT-2
Distance–X (mm)900 1400
AFT-4◆Option・Fiber head

Example of use

Light emitting/receiving set
with one fiber cutter

Application

Core
Cable Detection distance (mm)Cable
Bending diameter specification length Without 7 segment With 7 segment Standard
radiusprice (￥)
With
No
With
No
(mm)
(mm) diagnosis(mm)
diagnosis diagnosis diagnosis
General- Transmission
Singlecore
Top view Screw type M4
purpose2000 480 820 410 600
R30 φ2.2
Open
type
φ1.0
General- Transmission
Singlecore
Top view Screw type M3
purposeOpen
2000 210 340 160 210
R20 φ1.0
type
φ0.5
General- Transmission
Single core
Top
view
Screw
type
M3
purpose
2000
R25
φ1.0
Open
490
300
800
420
type
φ0.75
General- Transmission
Screw type M3
Singlecore
Top view (Heat resistance 100ºC) R20 φ1.0
purposeOpen
2000 260 430 170 240
type
φ0.5
*With diagnosis: When sensing level monitoring function (O-100 mode) is used / Without diagnosis: When using only with ON/OFF*Light emitting and receiving set, respectively free cut. *Mounting bracket not included.
*Contact our sales division for corresponding heads other than the above.

Model

AFT-4
AFT-1
AFT-2
AFT-1-1

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Detection View
method direction

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
settingType

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

108

Slave Units(Sensor/Amplifier)

ASLINKAMP◆Fiber type

Base unit

Photoelectric TypeA state in which the extension unit isadded to the base unit
(Can be mounted on the DIN rail)
Up to 16 units (including a base unit)
can be additionally coupled.

Laser TypeFiber Type
Proximity Type

Cylinder Type
Photo Interrupter Type＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

24V
drop

ID (address)
Duplicate/
Not setDimension A: 9×54.1×27.5／: Not applicable －: Not determinedLine Monitor

Number of
I/O points

Small Display Unit
List of Specifications

DP/DN
shortcircuit

Model

Input/
outputspecifications

Input Output

TypeConsumption
current (mA) Connection

Transmission I/O
side
side

B289SB-01AF-CAM20-V

1

Fiber head (red light) Base 11

B289SB-01AF-CAS-V

1

Fiber head (red light) Extension 11

Dimension
(mm)
Mass
(g)

Pressure Type

Output max.
Input
resistance/ ON current (mA) Response Standard
1 point Per 1
Per 1
time
price (￥)(kΩ)
point common

2-wire type(non-insulation) A 14
2-wire type(non-insulation) A 9

Max. 2 cycle times

Open

Max. 2 cycle times

Open*The dimensions are values excluding the cable section and sensor head section.
*3 types of fiber head mounting adaptors (for φ1.0, φ1.3, φ2,2) are attached.
*Do not use a head which uses a fiber in which the number of cores is 217 or more.

＜ Outline Dimensional Drawings ＞

Unit: mm

B289SB-01AF-CAM20-V / B289SB-01AF-CAS-V■B289SB-01AF-CAM20-V■B289SB-01AF-CAS-V

(200)

(71)

UL style 2103
2-core×No.24AWG (Black) φ4.1

5

30.1

(5)

20

(3)

0.9
(4.5) (87.5)

27.5

27.5

(56)

5
3.8

49.1

(56)

3.8

49.1

0.9

9

(4.5) (87.5)* 3 types of fiber head mounting adaptors (for φ1.0, φ1.3, φ2.2) are attached.

30.1

20

(5)

(71)

Red: DPBlack: DNCore line coatingouter diameter φ1.5
Transmission cable

9(3)

ASLINKAMP* 3 types of fiber head mounting adaptors (for φ1.0, φ1.3, φ2.2) are attached.

0.8

9
9×n

0.8

■Additional coupling drawing（B289SB-01AF-CAM20-V / B289SB-01AF-CAS-V）

Functional icon indication*See page 15 fordetails on function.

109

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

A state in which the extension unit is added to the base unit
Up to 16 units (including a base unit) can be additionally coupled.
*In order to securely mount to the unit,
it is recommended to use a DIN rail stopper.

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKAMP＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

B289SB-01AF-CAM20-V
B289SB-01AF-CAS-V

Transmission signal error

OnLED
indication unit

Transmission signal reception

Off(including disconnection and
No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

On
IN
(Orange)
Off

Photoelectric Type
Laser Type

Input ON

Fiber Type

Input OFF

Proximity Type

*When alarm diagnosis function is enabled

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications◆Option・Fiber head

Example of use

Light emitting/receiving set
with one fiber cutter

Application

Core
Cable Detection distance (mm)Cable
Bending diameter specification length Without 7 segment With 7 segment Standard
radiusprice (￥)
With
No
With
No
(mm)
(mm) diagnosis(mm)
diagnosis diagnosis diagnosis
General- Transmission
Singlecore
Top view Screw type M4
purpose2000 480 820 410 600
R30 φ2.2
Open
type
φ1.0
General- Transmission
Singlecore
Top view Screw type M3
purposeOpen
2000 210 340 160 210
R20 φ1.0
type
φ0.5
General- Transmission
Single core
Top
view
Screw
type
M3
purpose
2000
R25
φ1.0
Open
490
300
800
420
type
φ0.75
General- Transmission
Screw type M3
Singlecore
Top view (Heat resistance 100ºC) R20 φ1.0
purposeOpen
2000 260 430 170 240
type
φ0.5
*With diagnosis: When sensing level monitoring function (O-100 mode) is used / Without diagnosis: When using only with ON/OFF*Light emitting and receiving set, respectively free cut. *Mounting bracket not included.
*Contact our sales division for corresponding heads other than the above.

Model

AFT-4
AFT-1
AFT-2
AFT-1-1

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Detection View
method direction

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
settingType

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

110

Type of AMP

Standard type

Proximity Type
Sensors with excellent
durability, performing
non-contact detection ofwork such as metal

Sputter ready typeNon-shield type

Amplifier built-in
Full stainless steel bodytype

Chemical-capable(fluorine resin body) type

Polyarylate body type
IP68

All metal detection type

Amplifier relay

111

AnyWireASLINK System

Amplifier relay type

Detection distanceAppearance

Protective
structure

Model

Sensing
SensorInterference
level
sensitivity setting measuremonitoring
read/write
unnecessary
O
N
O
F
F

0 ～ 1mm

Maximum value○○

ThresholdMinimum value

Interference
countermeasure

RAS
function×○

unnecessary

BS-K1117-M08-□□□□

0 ～ 2mmIP67

0 ～ 5mm
0 ～ 10mm

IP67

0 ～ 10mm

BS-K1217-M08-□□□□

0 ～ 6.8mm
0 ～ 12mm

IP67

0 ～ 20mm

0 ～ 3.8mm

IP67

BS-K1117C-M12-□□□□
IP67
company standard
oil resistance*1

BS-K1117C-M18-□□□□
BS-K1117C-M30-□□□□

0 ～ 10mm

BS-K1118-M12-□□□□

0 ～ 2mm
IP68

BS-K1118-M18-□□□□
BS-K1118-M30-□□□□

0 ～ 10mm

BS-K4117-M12-□□□□

0 ～ 2mm
0 ～ 5mm

BS-K1117M-M18-□□□□
BS-K1117M-M30-□□□□

0 ～ 2mm

0 ～ 5mm

BS-K1217-M18-□□□□

BS-K1117M-M12-□□□□

0 ～ 8mm

0 ～ 5mm

BS-K1217-M12-□□□□

BS-K1217-M30-□□□□

0 ～ 1.6mm

IP67

BS-K4117-M18-□□□□
BS-K4117-M30-□□□□

0 ～ 10mm

0 ～ 0.6mm

BS-K1117S-M18-□□□□
BS-K1117S-M30-□□□□

0 ～ 3.4mm

0 ～ 1mm

BS-K1117-M18-□□□□

BS-K1117S-M12-□□□□

0 ～ 5mm0 ～ 0.8mm

BS-K1117-M12-□□□□

BS-K1117-M30-□□□□

0 ～ 2mm

0 ～ 1mm

Hi
LO
NG

RAS
function

IP67
company standard
oil resistance*1

BM-K1117G-S04-□□□□

IP67
company standard
oil resistance*1

BM-K1117G-M04-□□□□

BM-K1117G-S05-□□□□

BM-K1117G-M05-□□□□*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

AnyWireASLINK System

112

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (standard type) (IP67) Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K1117-M18-3012

BS-K1117-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

Dimension A: M8×51.8
Dimension B: M12×50.9
Dimension C: M18×50.5
Dimension D: M30×60.6＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BS-K1117-M08-3012

1

BS-K1117-M12-3012

1

BS-K1117-M18-3012

1

BS-K1117-M30-3012

1

BS-K1117-M08-1K

1

BS-K1117-M12-1K

1

BS-K1117-M18-1K

1

BS-K1117-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic Standard type0～1 13.8
induction
M8
Electromagnetic Standard type
0～2 8.4
induction
M12
Electromagnetic Standard type
0～5 8
induction
M18
Electromagnetic Standard type0～10 8.2
induction
M30
Electromagnetic Standard type0～1 13.8
induction
M8
Electromagnetic Standard type
0～2 8.4
induction
M12
Electromagnetic Standard type
0～5 8
induction
M18
Electromagnetic Standard type
0～108.2
induction
M30

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

Standard
detected object

Response Standard
time
price (￥)

A 21

Iron 8×8×1mm

Max. 10ms

Open

B 31 Iron 12×12×1mm Max. 10ms

Open

C 44 Iron 18×18×1mm

Max. 10ms

Open

D 107 Iron 30×30×1mm Max. 10ms

Open

A 28

Max. 10ms

Open

B 41 Iron 12×12×1mm Max. 10ms

Open

C 54 Iron 18×18×1mm

Max. 10ms

Open

D 117 Iron 30×30×1mm Max. 10ms

Open

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

Iron 8×8×1mm*The dimensions are numerical values excluding the cable section.
* Washers and nuts are included.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-K1117-M□□-3012
BS-K1117-M□□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

113

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area

・Influence by size and materialof detected object

・AD value-detection distance

BS-K1117-M08-□□□□

1.2

600

BS-K1117-M08-□□□□

1.200

X
0.4

-2.0

-1.0
0.0
1.0
Distance–Y (mm)

300
200

2.0

BS-K1117-M12-□□□□

BS-K1117-M12-□□□□

2.500
Detection distance–Y (mm)

1.0

300
200

-2

0
2
Distance–Y (mm)

0

4

900

0.8

1.6

2.4

3.2

4.0

AD value–Y (Digit)

Distance–X (mm)Y
X

2

BS-K1117-M18-□□□□

700
600

12

-4

0
4
Distance–Y (mm)400

8BS-K1117-M30-□□□□

900

0.0

AD value–Y (Digit)

Distance–X (mm)Y
X

4BS-K1117-M30-□□□□-100Distance–Y (mm)

700
600

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

400

10

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Cylinder Type
Photo Interrupter Type

Small Display Unit
List of Specifications

3
4
5
8
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)BS-K1117-M18-□□□□

5.000
4.000
3.000
2.000

12.000500
0Pressure Type

BS-K1117-M12-□□□□

1.000

0.000

2.0
4.0
6.0
8.0 10.0 12.0
Detection distance–X (mm)800
8Proximity Type

1.000

Detection distance–Y (mm)-8Fiber TypeLine Monitor

6.000

500
0

3
4
5
8
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)

1.500

0.000

4.8

800
4

Laser Type

2.000

Detection distance–X (mm)BS-K1117-M18-□□□□

6

0.0

Detection distance–Y (mm)-4Photoelectric Type

0.500

100
0.0

0.400

0.000

400

AD value–Y (Digit)

X

0.600

0

500

Y

0.800

0.200

0.00 0.40 0.80 1.20 1.60 2.00 2.40
Detection distance–X (mm)BS-K1117-M08-□□□□

1.000

100

600

2.0
Distance–X (mm)Detection distance–Y (mm)

Y

0.0

400

AD value–Y (Digit)

Distance–X (mm)

500
0.8

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

3458
12 18 30 54
Iron
Stainless steel
Aluminum
CopperBrass
Length of one side of detected object–X (mm)BS-K1117-M30-□□□□

10.000
8.000
6.000
4.000
2.000

0.0

0.000

4.0 8.0 12.0 16.0 20.0 24.0
Detection distance–X (mm)Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System114◆Proximity type (standard type) (IP67) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1117-M08-3012

6.3

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

33

φ15

Photoelectric Type

18.8

4

12

Setting port
（300）

8

44.7
φ14.9

2

Laser TypeFiber Type
M8×1

Transmission cable(Oil-proof and bending-proof type)

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

XS5H (plug)
Color: Black

Proximity Type
Pressure Type

1

ASLINKSENSOR BS-K1117-M12-3012

Cylinder Type11

Photo Interrupter TypeLine Monitor

Setting port

Small Display Unit
35.5

φ21
17

3

（300）

10

44.7

φ14.9

List of Specifications

15.4

Transmission cable(Oil-proof and bending-proof type)

M12×1

1

N/C

2

DP

3

N/C

3

4

4

DN

2

1

1

N/C

2

DP

XS5H (plug)
Color: Black17

ASLINKSENSOR BS-K1117-M18-3012

Setting port
φ29

15.5

35

24

4

（300）

10

φ14.9

44.7

M18×1

Transmission cable(Oil-proof and bending-proof type)

XS5H (plug)
Color: Black

3

N/C

3

4

4

DN

2

1

1

N/C

2

DP

28

ASLINKSENSOR BS-K1117-M30-3012

Setting port
φ42

43
5

36

17.6

（300）

10

φ14.9

44.7

M30×1.5

Transmission cable(Oil-proof and bending-proof type)

Functional icon indication*See page 15 fordetails on function.

115

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

3

N/C

4

4

DN

Transmission
line
short-circuit
detection

24V
drop

3

XS5H (plug)
Color: Black

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (standard type) (IP67) Cable＜ Outline Dimensional Drawings ＞

Unit: mm

6.3

ASLINKSENSOR BS-K1117-M08-1K

Setting port
φ15

33

18.8

4

12

（1000）

8

Core line coatingouter diameter φ1.5

Photoelectric TypeBlack: DN
Red: DP

Laser TypeTransmission cable(Oil-proof and bending-proof type)

M8×1

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BS-K1117-M12-1K

Cylinder Type11

Photo Interrupter TypeLine Monitor

Setting port
35.5

φ21
17

15.4

3

Small Display Unit

（1000）

10

List of Specifications

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M12×1

17

ASLINKSENSOR BS-K1117-M18-1K

Setting port
φ29

35

24

4

15.5

（1000）

10
Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M18×1

28

ASLINKSENSOR BS-K1117-M30-1K

Setting port
43

φ42
5

36

17.6

（1000）

10

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

116

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (sputter ready type) (IP67) Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K1117S-M30-3012

BS-K1117S-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

Dimension A: M12×50.9
Dimension B: M18×50.5
Dimension C: M30×60.6

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BS-K1117S-M12-3012

1

BS-K1117S-M18-3012

1

BS-K1117S-M30-3012

1

BS-K1117S-M12-1K

1

BS-K1117S-M18-1K

1

BS-K1117S-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic Sputter ready type0～2
M12
induction
Electromagnetic Sputter ready type
0～5
M18
induction
Electromagnetic Sputter ready type
0～10
M30
induction
Electromagnetic Sputter ready type0～2
M12
induction
Electromagnetic Sputter ready type
0～5
M18
induction
Electromagnetic Sputter ready type
0～10
M30
induction

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

8.4
8
8.2
8.4
8
8.2

Standard
detected object

Response Standard
time
price (￥)A 31 Iron 12×12×1mm Max. 10ms

Open

B 44 Iron 18×18×1mm Max. 10ms

Open

C 107 Iron 30×30×1mm Max. 10ms

Open

A 41 Iron 12×12×1mm Max. 10ms

Open

B 54 Iron 18×18×1mm Max. 10ms

Open

C 117 Iron 30×30×1mm Max. 10ms

Open

*The dimensions are numerical values excluding the cable section.
* Washers and nuts are included.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-K1117S-M□□-3012
BS-K1117S-M□□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

117

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area

600

BS-K1117S-M12-□□□□

2.500

AD value–Y (Digit)

Y
X

1.0

Detection distance–Y (mm)

500

2.0
Distance–X (mm)・Influence by size and materialof detected object

・AD value-detection distance

BS-K1117S-M12-□□□□

400
300
200
100

0.0

-4

-2

0
2
Distance–Y (mm)04Slave Units(Sensor/Amplifier)

ASLINKSENSOR

BS-K1117S-M12-□□□□

2.000
1.500
1.000

Photoelectric Type
0.500

Laser Type
0.0

0.8

1.6

2.4

3.2

4.0

0.000

4.8

Detection distance–X (mm)3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Fiber Type
Proximity Type
Pressure Type

BS-K1117S-M18-□□□□

6900

BS-K1117S-M18-□□□□YX

2

Detection distance–Y (mm)4

AD value–Y (Digit)

Distance–X (mm)

800
700
600
500
0

-8

12

-4

0
4
Distance–Y (mm)400

8BS-K1117S-M30-□□□□

900

0.0

BS-K1117S-M30-□□□□

X

4

-10

0
Distance–Y (mm)

700
600

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

400

10

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

4.000

Line Monitor

3.000

Small Display Unit

2.000

List of Specifications

1.000

3
4
5
8
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)BS-K1117S-M30-□□□□

10.000500
0Photo Interrupter Type12.000Detection distance–Y (mm)AD value–Y (Digit)

Distance–X (mm)Y

Cylinder Type

5.000

0.000

2.0
4.0
6.0
8.0 10.0 12.0
Detection distance–X (mm)

800
8

6.000

BS-K1117S-M18-□□□□

0.0

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

6.000
4.000
2.000
0.000

4.0 8.0 12.0 16.0 20.0 24.0
Detection distance–X (mm)Sensorcable
disconnection
detection

8.000

Transmission

DP/DN line
disconnection disconnection
detection

3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System118◆Proximity type (sputter ready type) (IP67) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1117S-M12-3012
11

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port
35.5

φ21
17

15.4

3

（300）

10

44.7

Photoelectric Type

φ14.9

2

Laser TypeFiber TypeTransmission cable(Oil-proof and bending-proof type)

M12×1

1

1

N/C

2

DP

3

N/C

3

4

4

DN

2

1

1

N/C

2

DP

Case:
Fluorine resin coating
Cable push: Made of fluorine resin
Head cover: Made of fluorine resin
Nut:
Fluorine resin coating

XS5H (plug)
Color: Black

Proximity Type
Pressure TypeASLINKSENSOR BS-K1117S-M18-3012
17

Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port

Small Display Unit

φ29

35

24

List of Specifications

4

15.5

（300）

10

φ14.9

44.7

M18×1

Transmission cable(Oil-proof and bending-proof type)

XS5H (plug)
Color: Black

3

N/C

3

4

4

DN

2

1

1

N/C

2

DP

Case:
Fluorine resin coating
Cable push: Made of fluorine resin
Head cover: Made of fluorine resin
Nut:
Fluorine resin coating

28

ASLINKSENSOR BS-K1117S-M30-3012

Setting port
φ42

43
5

36

17.6

（300）

10

φ14.9

44.7

M30×1.5
Transmission cable(Oil-proof and bending-proof type)

Functional icon indication*See page 15 fordetails on function.

119

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

3

3

N/C

4

4

DN

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

XS5H (plug)
Color: Black

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

Case:
Fluorine resin coating
Cable push: Made of fluorine resin
Head cover: Made of fluorine resin
Nut:
Fluorine resin coating

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (sputter ready type) (IP67) Cable＜ Outline Dimensional Drawings ＞

Unit: mm11

ASLINKSENSOR BS-K1117S-M12-1K

Setting port
35.5

φ21
17

15.4

3

（1000）

10

Core line coatingouter diameter φ1.5

Photoelectric TypeBlack: DN
Red: DP

Laser TypeTransmission cable(Oil-proof and bending-proof type)

M12×1

Case:
Fluorine resin coating
Cable push: Made of fluorine resin
Head cover: Made of fluorine resin
Nut:
Fluorine resin coating

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BS-K1117S-M18-1K

Cylinder Type17

Photo Interrupter TypeLine Monitor

Setting port

Small Display Unit

φ29

35

24

4

15.5

（1000）

List of Specifications

10
Core line coatingouter diameter φ1.5
Black: DN
Red: DP

Case:
Fluorine resin coating
Cable push: Made of fluorine resin
Head cover: Made of fluorine resin
Nut:
Fluorine resin coating

Transmission cable(Oil-proof and bending-proof type)

M18×1

28

ASLINKSENSOR BS-K1117S-M30-1K

Setting port
17.6

43

φ42
5

36

（1000）

10

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Case:
Fluorine resin coating
Cable push: Made of fluorine resin
Head cover: Made of fluorine resin
Nut:
Fluorine resin coating

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

120

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (Non-shield type) (IP67) Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K1217-M18-3012

BS-K1217-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

Dimension A: M8×51.8
Dimension B: M12×50.9
Dimension C: M18×50.5
Dimension D: M30×60.6＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BS-K1217-M08-3012

1

BS-K1217-M12-3012

1

BS-K1217-M18-3012

1

BS-K1217-M30-3012

1

BS-K1217-M08-1K

1

BS-K1217-M12-1K

1

BS-K1217-M18-1K

1

BS-K1217-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic Non-shield type
0～3.4 14.3
M8
induction
Electromagnetic Non-shield type
0～6.8 6.8
M12
induction
Electromagnetic Non-shield type0～12 6.7
M18
induction
Electromagnetic Non-shield type0～20 6.5
M30
induction
Electromagnetic Non-shield type
0～3.4 14.3
M8
induction
Electromagnetic Non-shield type
0～6.8 6.8
M12
induction
Electromagnetic Non-shield type0～12 6.7
M18
induction
Electromagnetic Non-shield type0～20 6.5
M30
induction

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

Standard
detected object

Response Standard
time
price (￥)A 20 Iron 20×20×1mm Max. 10ms

Open

B 29 Iron 30×30×1mm Max. 10ms

Open

C 38 Iron 30×30×1mm Max. 10ms

Open

D 90 Iron 54×54×1mm Max. 10ms

Open

A 27 Iron 20×20×1mm Max. 10ms

Open

B 37 Iron 30×30×1mm Max. 10ms

Open

C 45 Iron 30×30×1mm Max. 10ms

Open

D 96 Iron 54×54×1mm Max. 10ms

Open

*The dimensions are numerical values excluding the cable section.
* Washers and nuts are included.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-K1217-M□□-3012
BS-K1217-M□□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

121

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area
4.0

・AD value-detection distance

BS-K1217-M08-□□□□

600

AD value–Y (Digit)

Distance–X (mm)

X

2.0

4.000
Detection distance–Y (mm)500

Y・Influence by size and materialof detected object

BS-K1217-M08-□□□□

3.0
400
300
200

1.0
100
0.0
-6

8

-4

-2
0
2
Distance–Y (mm)

4

0

6

600

BS-K1217-M12-□□□□

300
200

2

8.000

100
0
-15

-10

-5
0
5
Distance–Y (mm)

10

0

15

X

4

0

700

600

500

-15

25

-10

-5
0
5
Distance–Y (mm)

10

400

15

0.0

6.0

BS-K1217-M30-□□□□

15

AD value–Y (Digit)

Distance–X (mm)

Y
X

10

600

500

5
0

700

-20

-10
0
10
Distance–Y (mm)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

400

20

Sensing
level
monitoring

ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Fiber Type
Proximity Type
Pressure Type

BS-K1217-M12-□□□□

Cylinder Type
Photo Interrupter Type

Small Display Unit
List of Specifications

3
4
5
8
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)

4.000

3
4
5
8
12 18 30 54
Iron
Stainless steel
Aluminum
CopperBrass
Length of one side of detected object–X (mm)BS-K1217-M30-□□□□

20.00015.00010.000
5.000

0.0

8.0

0.000

16.0 24.0 32.0 40.0 48.0

Detection distance–X (mm)Maximum value

54

8.000

25.000Detection distance–Y (mm)

800

30

12.0000.000

12.0 18.0 24.0 30.0 36.0

20

20

2.000

Detection distance–X (mm)BS-K1217-M30-□□□□

12

BS-K1217-M18-□□□□
Detection distance–Y (mm)AD value–Y (Digit)

Distance–X (mm)

Y

8

8

Line Monitor

0.000

0.00 3.40 6.80 10.20 13.60 17.00 20.40

800

5

4.000

BS-K1217-M18-□□□□

12

4

6.000

Detection distance–X (mm)BS-K1217-M18-□□□□

3

Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Detection distance–Y (mm)X

Photoelectric Type

1.000

0.000

0.00 0.80 1.60 2.40 3.20 4.00 4.80 5.60

400

AD value–Y (Digit)

Distance–X (mm)

Y

4

2.000

Laser Type500
6BS-K1217-M08-□□□□

3.000

Detection distance–X (mm)BS-K1217-M12-□□□□

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System122◆Proximity type (Non-shield type) (IP67) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1217-M08-3012

Setting port

7

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

51.8

φ15
6

12

（300）

27

18.8
44.7

4

2
φ14.9

Photoelectric Type
Laser Type
M8×1

Fiber TypeTransmission cable(Oil-proof and bending-proof type)

1

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

XS5H (plug)
Color: Black

Proximity Type
Pressure TypeASLINKSENSOR BS-K1217-M12-3012
11

Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port

Small Display Unit

35.5

φ21
7

17

28.5
3

10

44.7
φ14.9

List of Specifications

（300）

15.4

M12×1

N/C

2

DP

3

4

3

N/C

4

DN

2

1

1

N/C

2

DP

XS5H (plug)
Color: Black

Transmission cable(Oil-proof and bending-proof type)1

17

ASLINKSENSOR BS-K1217-M18-3012

Setting port
φ29
24

35
25
4
10

10

15.5

（300）

φ14.9

44.7

M18×1

Transmission cable(Oil-proof and bending-proof type)

3

N/C

3

4

4

DN

2

1

1

N/C

2

DP

XS5H (plug)
Color: Black28

ASLINKSENSOR BS-K1217-M30-3012

Setting port
φ42
36

13

43
30
5

17.6

（300）

10

φ14.9

44.7

*See page 15 fordetails on function.

123

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

4

3

N/C

4

DN

XS5H (plug) Color: Black
Transmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication

3

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (Non-shield type) (IP67) Cable＜ Outline Dimensional Drawings ＞

Unit: mm7

ASLINKSENSOR BS-K1217-M08-1K

Setting port
51.8

φ15
6

12

（1000）

27

18.8

4

Core line coatingouter diameter φ1.5

Photoelectric TypeBlack: DN
Red: DP

Laser TypeTransmission cable(Oil-proof and bending-proof type)

M8×1

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BS-K1217-M12-1K

Cylinder Type11

Photo Interrupter TypeLine Monitor
Setting port
35.5

φ21
7

17

15.4

Small Display Unit

（1000）

28.5
3

List of Specifications

10

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M12×1

17

ASLINKSENSOR BS-K1217-M18-1K

Setting port
φ29

10

24

35
25
4
10

15.5

（1000）

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M18×1

28

ASLINKSENSOR BS-K1217-M30-1K

Setting port
φ42

13

36

43
5

17.6

30

（1000）

10
Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

124

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (Full stainless steel body type) (IP67)
Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K1117M-M18-3012

BS-K1117M-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

Dimension A: M12×54.6
Dimension B: M18×52.4
Dimension C: M30×61.7

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BS-K1117M-M12-3012

1

BS-K1117M-M18-3012

1

BS-K1117M-M30-3012

1

BS-K1117M-M12-1K

1

BS-K1117M-M18-1K

1

BS-K1117M-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic Full stainless steel
inductionbody type M12 0～1.6
Electromagnetic Full stainless steel
inductionbody type M18 0～3.8
Electromagnetic Full stainless steel
inductionbody type M30 0～8
Electromagnetic Full stainless steel
inductionbody type M12 0～1.6
Electromagnetic Full stainless steel
inductionbody type M18 0～3.8
Electromagnetic Full stainless steel
inductionbody type M30 0～8

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

4.7
4.7
4.7
4.7
4.7
4.7

Standard
detected object

Response Standard
time
price (￥)A 32 Iron 12×12×1mm Max. 10ms

Open

B 47 Iron 30×30×1mm Max. 10ms

Open

C 107 Iron 54×54×1mm Max. 10ms

Open

A 39 Iron 12×12×1mm Max. 10ms

Open

B 55 Iron 30×30×1mm Max. 10ms

Open

C 115 Iron 54×54×1mm Max. 10ms

Open

*The dimensions are numerical values excluding the cable section.
* Washers and nuts are included.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-K1117M-M□□-3012
BS-K1117M-M□□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

125

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area

・Influence by size and materialof detected object

・AD value-detection distance

BS-K1117M-M12-□□□□

700

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

BS-K1117M-M12-□□□□

2.500

BS-K1117M-M12-□□□□

1.6

Y
X

0.8

Detection distance–Y (mm)AD value–Y (Digit)

Distance–X (mm)

600
1.2

500
400

2.000
1.500
1.000

Photoelectric Type

0.4

300

0.500

0.0

200

0.000

Laser Type
-4

-2

0
2
Distance–Y (mm)

4

0.0

0.8

1.6

2.4

3.2

4.0

4.8

Detection distance–X (mm)3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Fiber Type
Proximity Type
Pressure Type

4.0

600

AD value–Y (Digit)

Y
2.0

X

1.0

400
300

-4

0
4
Distance–Y (mm)

100

8

0.0

0.8

1.6

2.4

3.2

4.0

4.8

550
AD value–Y (Digit)

Distance–X (mm)List of Specifications

X
4.0

2.0

0.0

0.000

5.6

BS-K1117M-M30-□□□□

Y

6.0

10.000

450
350
250

0
Distance–Y (mm)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

50

10

Sensing
level
monitoring

ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

BS-K1117M-M30-□□□□

8.000
6.000
4.000

0.0

2.0

4.0

6.0

0.000

8.0 10.0 12.0 14.0

Detection distance–X (mm)Maximum value

3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)

2.000

150

-10

Small Display Unit

1.000

650

8.0

Line Monitor

2.000

Detection distance–X (mm)BS-K1117M-M30-□□□□

Photo Interrupter Type

3.000

200

-8

Cylinder Type

4.000

Detection distance–Y (mm)Distance–X (mm)BS-K1117M-M18-□□□□

500

3.0

0.0

BS-K1117M-M18-□□□□

Detection distance–Y (mm)BS-K1117M-M18-□□□□

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

3458
12 18 30 54
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System126◆Proximity type (Full stainless steel body type) (IP67) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1117M-M12-3012

11

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port

Photoelectric Type

φ21

39.2

17

3

15.4

（300）

10

44.7
2
φ14.9

Laser TypeFiber Type
M12×1

Proximity Type
Pressure TypeTransmission cable(Oil-proof and bending-proof type)

XS5H (plug)
Color: Black

1

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

ASLINKSENSOR BS-K1117M-M18-3012

Cylinder Type17

Photo Interrupter TypeLine Monitor
Small Display Unit

Setting port

φ29

36.9

24

List of Specifications

4

（300）

15.5
10

φ14.9

44.7

M18×1

XS5H (plug)
Color: Black

Transmission cable(Oil-proof and bending-proof type)

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

28

ASLINKSENSOR BS-K1117M-M30-3012

Setting port
φ42

44.1

36

5

17.6

（300）

10

φ14.9

44.7

M30×1.5

Transmission cable(Oil-proof and bending-proof type)

Functional icon indication*See page 15 fordetails on function.

127

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

3

XS5H (plug)
Color: Black

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

4

1

N/C

2

DP

3

N/C

4

DN

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (Full stainless steel body type) (IP67) Cable＜ Outline Dimensional Drawings ＞

Unit: mm11

ASLINKSENSOR BS-K1117M-M12-1K

Setting port
φ21

39.2

17

3

15.4

（1000）

10

Core line coatingouter diameter φ1.5

Photoelectric TypeBlack: DN
Red: DP

Laser TypeFiber TypeTransmission cable(Oil-proof and bending-proof type)

M12×1

Proximity Type
Pressure TypeASLINKSENSOR BS-K1117M-M18-1K

Cylinder Type17

Photo Interrupter TypeLine Monitor

Setting port
φ29

36.9

24

4

15.5

Small Display Unit

（1000）

List of Specifications

10
Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M18×1

28

ASLINKSENSOR BS-K1117M-M30-1K

Setting port
φ42

44.1

36

5

17.6

（1000）

10
Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

128

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (chemical-capable (fluorine resin body) type)(IP67 company standard oil resistance*1) Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K1117C-M18-3012

BS-K1117C-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type

Photo Interrupter Type＜ Specifications ＞
O
NLine Monitor

O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

Dimension A: M12×50.9
Dimension B: M18×51.5
Dimension C: M30×60.6

ID (address)
Duplicate/
Not set24V
drop／: Not applicable －: Not determined

Small Display Unit

Number of
I/O points

List of Specifications

Input/
outputInput Output specifications

Model
BS-K1117Ｃ-M12-3012

1

BS-K1117Ｃ-M18-3012

1

BS-K1117Ｃ-M30-3012

1

BS-K1117Ｃ-M12-1K

1

BS-K1117Ｃ-M18-1K

1

BS-K1117Ｃ-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic Chemical-capable type0～2
induction
M12
Electromagnetic Chemical-capable type
0～5
induction
M18
Electromagnetic Chemical-capable type
0～10
induction
M30
Electromagnetic Chemical-capable type0～2
induction
M12
Electromagnetic Chemical-capable type
0～5
induction
M18
Electromagnetic Chemical-capable type
0～10
induction
M30

Dimension
(mm)
Mass
(g)

Cylinder Type2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

6.9
7.0
7.0
6.9
7.0
7.0

Standard
detected object

Response Standard
time
price (￥)A 24 Iron 12×12×1mm Max. 10ms

Open

B 34 Iron 18×18×1mm Max. 10ms

Open

C 68 Iron 30×30×1mm Max. 10ms

Open

A 31 Iron 12×12×1mm Max. 10ms

Open

B 40 Iron 18×18×1mm Max. 10ms

Open

C 76 Iron 30×30×1mm Max. 10ms

Open

*The dimensions are numerical values excluding the cable section.

◆Option・SUS washers

Product specifications

Standard
price (￥)SUS washer for M12 (one washer)Open

SUS washer for M18 (one washer)

Open

Model

Washers sold separately for the proximity type (chemical-capable type).
No washer is included for the proximity type because both the body and included
BS-K-M12-SW
nuts are made of fluorine resin, which can be easily damaged. However, since the
BS-K-M18-SW
tightening torque is set to a small value, washers are offered as an option to firmly
lock the nuts. Purchase them as necessary.
(There is no optional washer for the M30 type, as it can be firmly tightened without a washer.)＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-K1117C-M□□-3012
BS-K1117C-M□□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

129

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area

500

Y

BS-K1117C-M12-□□□□

2.5

AD value–Y (Digit)

21

Detection distance–Y (mm)

400

X

3
Distance–X (mm)・Influence by size and materialof detected object

・AD value-detection distance

BS-K1117C-M12-□□□□

4

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

300
200
100

BS-K1117C-M12-□□□□

2
1.5
1

Photoelectric Type
0.5

Laser Type
0

-8

-4

0
4
Distance–Y (mm)

0

8

0.0

0.8

1.6

2.4

3.2

4.0

0

4.8

0

10

20

30

40

50

60

Fiber Type

Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Detection distance–X (mm)Proximity Type
Pressure Type

BS-K1117C-M18-□□□□

BS-K1117C-M18-□□□□

10

6
Detection distance–Y (mm)800
X

AD value–Y (Digit)

Distance–X (mm)

Y
8
6
4

600

500

2
0

700

-12

-8

-4
0
4
Distance–Y (mm)

8

400

12

800

0.0

2.0

4.0

6.0

8.0

BS-K1117C-M30-□□□□

Line Monitor

3

Small Display Unit

2

List of Specifications

12
Detection distance–Y (mm)Y

AD value–Y (Digit)

Distance–X (mm)40

10.0 12.0 14.0

700
X

6
4

600

500

2
0

Photo Interrupter Type

1

10
8

Cylinder Type

5

Detection distance–X (mm)BS-K1117C-M30-□□□□

BS-K1117C-M18-□□□□

0

10
20
30
40
50
60
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)BS-K1117C-M30-□□□□

10
8
6
4
2

-12

-8

-4

0

4

8

400

12

Distance–Y (mm)

0.0

4.0

8.0

0

12.0 16.0 20.0 24.0 28.0

Detection distance–X (mm)

0

10
20
30
40
50
60
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

130

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (chemical-capable (fluorine resin body) type)◆(IP67 company standard oil resistance*1) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1117C-M12-3012

Setting port
35.5

17

15.4

（300）

6

44.7

Photoelectric Type

2
φ14.9

Laser TypeFiber Type

M12×1

Proximity Type
Pressure TypeTransmission cable(Oil-proof and bending-proof type)

1

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

XS5H (plug)
Color: BlackASLINKSENSOR BS-K1117C-M18-3012

Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port

Small Display Unit
List of Specifications

8

36

15.5

（300）
44.7

φ14.9

24

M18×1

Transmission cable(Oil-proof and bending-proof type)

XS5H (plug)
Color: Black

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

ASLINKSENSOR BS-K1117C-M30-3012

Setting port
36

8

43

17.6

（300）

φ14.9

44.7

Transmission cable
M30×1.5 (Oil-proof and bending-proof type)

Functional icon indication*See page 15 fordetails on function.

131

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

3

XS5H (plug)
Color: Black

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

4

1

N/C

2

DP

3

N/C

4

DN

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (chemical-capable (fluorine resin body) type)(IP67 company standard oil resistance*1) Cable＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1117C-M12-1K

Setting port
35.5

17

15.4

（1000）

6
Core line coatingouter diameter φ1.5

M12×1

Photoelectric TypeBlack: DN
Red: DP

Laser TypeTransmission cable(Oil-proof and bending-proof type)

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BS-K1117C-M18-1K

Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port
36

24

15.5

Small Display Unit

（1000）

List of Specifications

8
Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M18×1

ASLINKSENSOR BS-K1117C-M30-1K

Setting port
43

36

17.6

（1000）

8

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

132

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆ Proximity type (polyarylate body type, IP68) Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K1118-M18-3012

BS-K1118-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

Dimension A: M12×51.6
Dimension B: M18×52.1
Dimension C: M30×61.3

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BS-K1118-M12-3012

1

BS-K1118-M18-3012

1

BS-K1118-M30-3012

1

BS-K1118-M12-1K

1

BS-K1118-M18-1K

1

BS-K1118-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic Polyarylate body type0～2
induction
M12
Electromagnetic Polyarylate body type
0～5
induction
M18
Electromagnetic Polyarylate body type
0～10
induction
M30
Electromagnetic Polyarylate body type0～2
induction
M12
Electromagnetic Polyarylate body type
0～5
induction
M18
Electromagnetic Polyarylate body type
0～10
induction
M30

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

6.9
7.0
7.0
6.9
7.0
7.0

Standard
detected object

Response Standard
time
price (￥)A 23 Iron 12×12×1mm Max. 10ms

Open

B 30 Iron 18×18×1mm Max. 10ms

Open

C 62 Iron 30×30×1mm Max. 10ms

Open

A 30 Iron 12×12×1mm Max. 10ms

Open

B 38 Iron 18×18×1mm Max. 10ms

Open

C 70 Iron 30×30×1mm Max. 10ms

Open

*The dimensions are numerical values excluding the cable section.
No washer is included because the device is made of polyarylate resin, which can be easily damaged.
Since the tightening torque is set to a larger value than that for the chemical-capable type (p. 129), SUS washers (p.129) are not offered as an option. However, they can beused as necessary.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BS-K1118-M□□-3012
BS-K1118-M□□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

133

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area

500
Y

BS-K1118-M12-□□□□

2.5

AD value–Y (Digit)

21

Detection distance–Y (mm)

400

X

3
Distance–X (mm)・Influence by size and materialof detected object

・AD value-detection distance

BS-K1118-M12-□□□□

4

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

300
200
100

BS-K1118-M12-□□□□

2
1.5
1

Photoelectric Type
0.5

Laser Type
0

-8

-4

0
4
Distance–Y (mm)

0

8

0.0

0.8

1.6

2.4

3.2

4.0

0

4.8

0

10

20

30

40

50

60

Fiber Type

Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Detection distance–X (mm)Proximity Type
Pressure Type

BS-K1118-M18-□□□□

BS-K1118-M18-□□□□

10

6
Detection distance–Y (mm)800
X

AD value–Y (Digit)

Distance–X (mm)

Y
8
6
4

600

500

2
0

700

-12

-8

-4
0
4
Distance–Y (mm)

8

400

12

800

0.0

2.0

4.0

6.0

8.0

BS-K1118-M30-□□□□

Line Monitor

3

Small Display Unit

2

List of Specifications

12
Detection distance–Y (mm)Y

AD value–Y (Digit)

Distance–X (mm)40

10.0 12.0 14.0

700
X

6
4

600

500

2
0

Photo Interrupter Type

1

10
8

Cylinder Type

5

Detection distance–X (mm)BS-K1118-M30-□□□□

BS-K1118-M18-□□□□

0

10
20
30
40
50
60
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)BS-K1118-M30-□□□□

10
8
6
4
2

-12

-8

-4

0

4

8

400

12

Distance–Y (mm)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

0.0

4.0

8.0

0

12.0 16.0 20.0 24.0 28.0

Detection distance–X (mm)Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

0

10
20
30
40
50
60
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

134

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆ Proximity type (polyarylate body type, IP68) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1118-M12-3012

Setting port

17

4

Photoelectric Type

35.5

（300）

16.1

44.7
φ14.9

2

Laser Type
M12×1

Fiber TypeTransmission cable(Oil-proof and bending-proof type)

XS5H (plug)
Color: Black

1

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

Proximity Type
Pressure TypeASLINKSENSOR BS-K1118-M18-3012

Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit

Setting port
24

List of Specifications

36

（300）

16.1

4

φ14.9

44.7

M18×1

XS5H (plug)
Color: Black

Transmission cable(Oil-proof and bending-proof type)

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

ASLINKSENSOR BS-K1118-M30-3012

Setting port
36

5

43

18.3

（300）

φ14.9

44.7

M30×1.5

Transmission cable(Oil-proof and bending-proof type)

Functional icon indication*See page 15 fordetails on function.

135

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

3

XS5H (plug)
Color: Black

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

4

1

N/C

2

DP

3

N/C

4

DN

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆ Proximity type (polyarylate body type, IP68) Cable＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K1118-M12-1K

Setting port
35.5

17

16.1

(1000)

4

Core line coatingouter diameter φ1.5

Photoelectric TypeBlack: DN
Red: DP

Laser TypeTransmission cable(Oil-proof and bending-proof type)

M12×1

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BS-K1118-M18-1K

Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port
24

36

16.1

Small Display Unit

(1000)

List of Specifications

4Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M18×1

ASLINKSENSOR BS-K1118-M30-1K

Setting port
36

43

18.3

(1000)

5

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

136

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆ Proximity type (all metal detection type) (IP67) Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BS-K4117-M18-3012

BS-K4117-M18-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

Dimension A: M12×50.9
Dimension B: M18×50.5
Dimension C: M30×60.6

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BS-K4117-M12-3012

1

BS-K4117-M18-3012

1

BS-K4117-M30-3012

1

BS-K4117-M12-1K

1

BS-K4117-M18-1K

1

BS-K4117-M30-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Electromagnetic All metal detection type0～2
induction
M12
Electromagnetic All metal detection type
0～5
induction
M18
Electromagnetic All metal detection type
0～10
induction
M30
Electromagnetic All metal detection type0～2
induction
M12
Electromagnetic All metal detection type
0～5
induction
M18
Electromagnetic All metal detection type
0～10
induction
M30

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

13
13
13
13
13
13

Standard
detected object

Response Standard
time
price (￥)A 31 Aluminum 12×12×3mm Max. 10ms

Open

B 42 Aluminum 18×18×3mm Max. 10ms

Open

C 98 Aluminum 30×30×3mm Max. 10ms

Open

A 37 Aluminum 12×12×3mm Max. 10ms

Open

B 49 Aluminum 18×18×3mm Max. 10ms

Open

C 105 Aluminum 30×30×3mm Max. 10ms

Open

*The dimensions are numerical values excluding the cable section.
* Washers and nuts are included.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) FlashingTransmission signal reception(including disconnection and

No transmission signal reverse connection of DP and DN)

Off
ALM
(Red)

BS-K4117-M□□-3012
BS-K4117-M□□-1K

Transmission signal error

On

On

Sensing level decrease*

Flashing

Slave unit voltage decreaseLED
indication unit

(ON for 0.2 seconds,
OFF for 1.0 second)

Flashing

Teaching error(Flashing every 0.1 second）

LINK
ALM

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

137

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)・Detection area
BS-K4117-M12-□□□□

BS-K4117-M12-□□□□

2.5

BS-K4117-M12-□□□□

800

Y
X
AD value–Y (Digit)

3
Distance–X (mm)・Influence by size and materialof detected object

・AD value-detection distance

Detection distance–Y (mm)4

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

2

600

400

1

200

0

0

2
1.5
1

Photoelectric Type
0.5

Laser Type
-8

-4
Iron

0

4

8

Stainless steel
Brass
Aluminum
Distance–Y (mm)Copper0

0.8 1.6 2.4 3.2
4Detection distance–X (mm)

0

6

0

10

20

30

40

50

60

Fiber Type

Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Proximity Type
Pressure Type

800

6

600
AD value–Y (Digit)

Distance–X (mm)5BS-K4117-M18-□□□□

Detection distance–Y (mm)6BS-K4117-M18-□□□□

4
Y

3

X

2

400

200
1
-12
Iron

-8
-4
0
4
8
Stainless steel
Brass
Aluminum
Distance–Y (mm)012Copper

BS-K4117-M30-□□□□

3

5

Photo Interrupter Type

4Line Monitor

3

Small Display Unit

2

List of Specifications

0

4.8
5.4
8
11 13
Detection distance–X (mm)

12

800

8

Y

AD value–Y (Digit)

Distance–X (mm)0BS-K4117-M30-□□□□

10

X

6
4

600

400

200

2
0

Cylinder Type1

Detection distance–Y (mm)0BS-K4117-M18-□□□□

-4

-8

8

12

Iron

Stainless steel
Brass
Aluminum
Distance–Y (mm)CopperFunctional icon indication*See page 15 fordetails on function.

0

O
N
O
F
F

Hi
LO
NG

4

0

-12

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

0

10
20
30
40
50
60
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)BS-K4117-M30-□□□□

10
8
6
4
2

0

4

8
10.5 1317
21
Detection distance–X (mm)Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

025

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

0

10
20
30
40
50
60
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System138◆ Proximity type (all metal detection type) (IP67) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BS-K4117-M12-3012
11

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port
35.5

φ21
17

Photoelectric Type

（300）

10

44.7

Fiber Type

φ14.9

φ9.5

2

Laser Type

M12×1

Transmission cable(Oil-proof and bending-proof type)

Proximity Type
Pressure Type

15.4

3

1

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

XS5H (plug)
Color: BlackASLINKSENSOR BS-K4117-M18-3012
17

Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port

Small Display Unit
φ29
24

10

15.5

（300）
44.7

φ14.9

List of Specifications

35
4

M18×1

Transmission cable(Oil-proof and bending-proof type)

3

4

2

1

1

N/C

2

DP

3

N/C

4

DN

XS5H (plug)
Color: Black28

ASLINKSENSOR BS-K4117-M30-3012

Setting port

φ42
36

43
5

10

17.6

（300）

φ14.9

44.7

3

M30×1.5

Transmission cable(Oil-proof and bending-proof type)

Functional icon indication*See page 15 fordetails on function.

139

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

4

1

N/C

2

DP

3

N/C

4

DN

XS5H (plug)
Color: Black

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆ Proximity type (all metal detection type) (IP67) Cable＜ Outline Dimensional Drawings ＞

Unit: mm11

ASLINKSENSOR BS-K4117-M12-1K

Setting port
35.5

φ21
17

（1000）

15.4
10

Core line coatingouter diameter φ1.5

φ9.5

3

M12×1

Photoelectric TypeBlack: DN
Red: DP

Laser TypeTransmission cable(Oil-proof and bending-proof type)

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BS-K4117-M18-1K
17Cylinder Type
Photo Interrupter TypeLine Monitor
Setting port
φ29
24

35
4

10

15.5

Small Display Unit

（1000）

List of Specifications
Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M18×1

28

ASLINKSENSOR BS-K4117-M30-1K

Setting port

φ42
36

43
5

10

17.6

（1000）

Core line coatingouter diameter φ1.5
Black: DN
Red: DPTransmission cable(Oil-proof and bending-proof type)

M30×1.5

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

140

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (amplifier relay type) (IP67 company standard oil resistance*1)
Cable with M12 connector/Cable

Photoelectric Type
Laser TypeFiber Type

BM-K1117G-M05-3012

BM-K1117G-S04-1K

Proximity Type*Contact our sales division
for attachment fittings.

Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

Amplifier Dimension A,B,C,D＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

Common: 14×38×7.5

DP/DN
disconnection

DP/DN
shortcircuit

Head Dimension A: φ4×16

Dimension B: φ5.4×16
Dimension C: M4×16 Dimension D: M5×16

ID (address)
Duplicate/
Not set24V
drop

Input/
outputInput Output specifications

Model
BM-K1117G-S04-3012

1

BM-K1117G-S05-3012

1

BM-K1117G-M04-3012

1

BM-K1117G-M05-3012

1

BM-K1117G-S04-1K

1

BM-K1117G-S05-1K

1

BM-K1117G-M04-1K

1

BM-K1117G-M05-1K

1

Type

Consumption
Detection current (mA)
Connection
distance
ssion I/O(mm) Transmi
side
side

Dimension
(mm)
Mass
(g)

／: Not applicable －: Not determined

Number of
I/O points

2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

A 22

Max. 10ms

Open

B 23

Max. 10ms

Open

Max. 10ms

Open(The detection distance Max. 10ms

Open

Electromagnetic Amplifier relay type
induction
φ4Electromagnetic Amplifier relay type
induction
φ5.4Electromagnetic Amplifier relay type
induction
φ4Electromagnetic Amplifier relay type
induction
φ5Electromagnetic Amplifier relay type
induction
φ4Electromagnetic Amplifier relay type
induction
φ5.4Electromagnetic Amplifier relay type
induction
M4
Electromagnetic Amplifier relay type
induction
M5

0～0.8 6.3
0～1

6.5

0～0.6 5.9
0～1

6.4

0～0.8 6.3
0～1

6.5

0～0.6 5.9
0～1

6.4

C 22
D 23
A 30

Standard
detected object

Response Standard
time
price (￥)

Iron 5×5×1mm

is shorter for
non-magnetic metal.)Max. 10ms

Open

B 31

Max. 10ms

Open

C 30

Max. 10ms

Open

D 31

Max. 10ms

Open*The dimensions are numerical values excluding the cable section.

＜ LED indication ＞
LEDsymbolIndication status

Detailed status

LINK(Green) Flashing

ALM
(Red)

LINK
ALM

BM-K1117G-□0□-3012
BM-K1117G-□0□-1K

Transmission signal error

OnTransmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

LED
indication unit

Input ONOn
IN
(Orange)
Off

Input OFF
*When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

141

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

＜ Characteristic diagram ＞ (Reference value)BM-K1117G-S04-□□□□

600

1.0

500

0.8

400

0.6

AD value–Y (Digit)

Distance–X (mm)1.2・Influence by size and materialof detected object

・AD value-detection distance

Y
X

0.4

BM-K1117G-S04-□□□□

1.000
Detection distance–Y (mm)・Detection area

300
200

0.600
0.400

Photoelectric Type

100

0.200

0.0

0

0.000

-2

-1
0
1
Distance–Y (mm)2

3BM-K1117G-S04-□□□□

0.800

0.2

-3

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Laser Type
0.00

0.40

0.80

1.20

1.60

3

4

5

8

12

18

30

Fiber Type

Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)Detection distance–X (mm)Proximity Type
Pressure Type

0.8

400

0.6

X

0.4

300
200

0.2

100

0.0

0

-3

-2

-1
0
1
Distance–Y (mm)2

3BM-K1117G-M04-□□□□

600

1.0

500

0.8

400

0.6
Y

0.4

1.400

0.00

0.40
0.80
1.20
1.60
Detection distance–X (mm)BM-K1117G-M04-□□□□

200

0

-2

-1
0
1
Distance–Y (mm)2

3BM-K1117G-M05-□□□□

600

1.0

500

0.8

400

AD value–Y (Digit)

Distance–X (mm)

1.2

-3

0.6
Y
0.4

X

0.2
0.0

0.00

0.40
0.80
1.20
Detection distance–X (mm)

-2

-1
0
1
Distance–Y (mm)2

BM-K1117G-M05-□□□□

List of Specifications

0.400

3
4
5
8
12
18
30
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)BM-K1117G-M04-□□□□

0.700
0.600
0.500
0.400
0.300
0.200

1.400

300
200

0
0.00

3

Small Display Unit

0.600

0.000

1.60

100

-3

Line Monitor

0.800

0.100

Detection distance–Y (mm)0.0

Photo Interrupter Type

1.000

0.800

X
100

Cylinder Type

1.200

0.000

2.00

300

0.2

BM-K1117G-S05-□□□□

0.200

Detection distance–Y (mm)Y

BM-K1117G-S05-□□□□

Detection distance–Y (mm)500
AD value–Y (Digit)

1.0

1.2

Distance–X (mm)600

AD value–Y (Digit)

Distance–X (mm)1.2

BM-K1117G-S05-□□□□

3
4
5
8
12
18
30
Iron
Stainless steel
Aluminum
CopperBrass
Length of one side of detected object–X (mm)BM-K1117G-M05-□□□□

1.200
1.000
0.800
0.600
0.400
0.200

0.40
0.80
1.20
1.60
Detection distance–X (mm)

0.000

2.00

3
4
5
8
12
18
30
Iron
Stainless steel
Brass
Aluminum
CopperLength of one side of detected object–X (mm)*1 Oil resistance has been confirmed by using oil/cutting oil specified by us*. The device is resistant to oil but there is no guarantee that breakdown will not occur. Do not use the device when it isconstantly exposed to oil splashing or under oil jet flow.
* Cutting oil specified by us: Water-insoluble (YUSHIRON CUT KM557, KZ313S), Water-soluble (YUSHIROKEN EC50, AP-EX-E7, FGS700)∙∙∙Immersion at an ambient temperature of 55°C
* Lubricating oil specified by us: (VELOCITY OIL No.3)∙∙∙Immersion at an ambient temperature of 55°C

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System142◆Proximity type (amplifier relay type) (IP67 company standard oil resistance*1) Cable with M12 connector＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR BM-K1117G-S04-3012

14

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port
（300）

Photoelectric Type38

Fiber Type

DP

3

N/C

4

DN

1

3

4

300

16
7.5

2

2

φ14.9

Laser Type

N/C

φ4

44.7
1

XS5H (plug)
Color: Black

Transmission cable(Oil-proof and bending-proof type)

Head cable

Proximity Type
Pressure TypeASLINKSENSOR BM-K1117G-S05-3012

Cylinder Type
14

Photo Interrupter TypeLine Monitor

Setting port

Small Display Unit

2

DP

3

N/C

4

DN

3

4

38

44.7

300

16

7.5

N/C

1
φ14.9

1

2

φ5.4

（300）

List of Specifications

XS5H (plug)
Color: Black

Transmission cable
Head cable(Oil-proof and bending-proof type)14

ASLINKSENSOR BM-K1117G-M04-3012

Setting port
（300）
38

44.7
2

DP

3

N/C

4

DN

2

1

3

4

300

16

7.5

N/C

φ14.9

1

XS5H (plug)
Color: Black

Transmission cable(Oil-proof and bending-proof type)

M4×0.5

Head cable

14

ASLINKSENSOR BM-K1117G-M05-3012

Setting port
（300）
38

Functional icon indication*See page 15 fordetails on function.

143

O
N
O
F
F

Hi
LO
NG

N/C

2

DP

2

1

4

3

N/C

4

DN

3

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

16

Reading/
writing of
sensorsensitivity
setting

7.5

1

300

φ14.9

44.7

XS5H (plug)
Color: Black

Sensorcable
disconnection
detection

Transmission cable(Oil-proof and bending-proof type)Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

Head cable

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

M5×0.524V
dropTransmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Proximity type (amplifier relay type) (IP67 company standard oil resistance*1) Cable＜ Outline Dimensional Drawings ＞

Unit: mm14

ASLINKSENSOR BM-K1117G-S04-1K

Setting port
Core line coatingouter diameter φ1.5

38

300

16

Photoelectric Typeφ4（1000）

7.5

DN (Black)
DP (Red)Transmission cable(Oil-proof and bending-proof type)

Laser Type

Head cable

Fiber Type
Proximity Type
Pressure TypeASLINKSENSOR BM-K1117G-S05-1K

Cylinder Type

14

Photo Interrupter TypeLine Monitor
Small Display Unit
Setting port
38

300

16

DN (Black)
DP (Red)Transmission cable(Oil-proof and bending-proof type)

List of Specifications

7.5（1000）

φ5.4

Core line coatingouter diameter φ1.5

Head cable

14

ASLINKSENSOR BM-K1117G-M04-1K

Setting port
（1000）

Core line coatingouter diameter φ1.5

38

300

16

7.5

DN (Black)
DP (Red)Transmission cable(Oil-proof and bending-proof type)

M4×0.5

Head cable

14

ASLINKSENSOR BM-K1117G-M05-1K

Setting port
（1000）

Core line coatingouter diameter φ1.5

38

300

16

7.5

DN (Black)
DP (Red)Head cable

Transmission cable(Oil-proof and bending-proof type)

M5×0.5

See “*1” on page 142.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

144

Pressure Type
Source pressure for
equipment or adsorption
pressure can be detectedby detection of pressure ofgas such as air.

Cylinder Type
Piston position ismonitored by detection ofmagnetic force in thecylinder piston.

Photo InterrupterType
Sensor consisting of lightemitting/receiving elements
which detects an object
when it blocks light

145

AnyWireASLINK System

Type of AMP

Type

Amplifier built-in

PressureType of AMP

Amplifier relay
Amplifier built-in

Type of AMP

Amplifier built-in

CylinderType

Photo interrupter

Gauge pressure

Appearance

ModelInterference
Sensing
Sensorlevel
sensitivity setting measureunnecessary
monitoring
read/write
Hi
LO
NG

Maximum value

○

○

○

Sensing
SensorInterference
level
sensitivity setting measuremonitoring
read/write
unnecessary

RAS
function

O
N
O
F
F

Low positive pressure: 0~100kPa

B284SB-□□-1KPLP30

Positive pressure: 0~1000kPa

B284SB-□□-1KPP30

Negative pressure: 0~ −100kPa

B284SB-□□-1KNP30

Compound pressure: −100~100kPa

B284SB-□□-1KLP30

Type

Appearance

Model

○

○

Sensing
SensorInterference
level
sensitivity setting measuremonitoring
read/write
unnecessary

RAS
function

B285SB-01-1K1

Model

O
N
O
F
F

5mm (groove width)

B297SB-01-1K40

Interference
countermeasure

RAS
function○

BM-C27-DM9-□□-5050

Appearance

unnecessary

Maximum value

O
FF

Detection distanceThresholdMinimum value

Hi
LO
NG

O
N

Corresponding to cylinder roundgroove manufactured by SMC

Interference
countermeasure

RAS
function

ThresholdMinimum value

Hi
LO
NG

Maximum value○×

ThresholdMinimum value

unnecessary

Interference
countermeasureunnecessary

RAS
function

RAS
function○

AnyWireASLINK System

146

◆Pressure type＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR B284SB-0□-1K□□P30 / B284SB-J1-1K□P30
4.5■Back side details
20
8.4

22.3

7.5

M5 female screw
Depth 4

Transmission connector
PA connector of JST
B03B-PASK-1

20

8.3

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

2-M3
Attachment frame
30

Photoelectric TypeM5 female screw
Depth 4Laser Type30

Fiber Type
Proximity TypeAttachment plate(1 to 6mm)

Pressure Type

Setting port

Attachment fitting

Photo Interrupter Type＜ Specifications ＞
O
NLine Monitor

O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 30×30×26.8／: Not applicable －: Not determined

Small Display Unit
List of Specifications

Number of Input/
I/O points
output Type
Input Output specifications

Model
B284SB-01-1KPLP30

1

B284SB-02-1KPLP30

2

B284SB-01-1KPP30

1

B284SB-02-1KPP30

2

B284SB-01-1KNP30

1

B284SB-02-1KNP30

2

B284SB-01-1KLP30

1

B284SB-02-1KLP30

2

B284SB-J1-1KPLP30

16

B284SB-J1-1KPP30

16

B284SB-J1-1KNP30

16

B284SB-J1-1KLP30

162-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

Max. 10ms

Open

Max. 10ms

Open

Max. 10ms

Open

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

A 25

Max. 10ms

Open

Transmission I/O
side
side

Low positive pressure
Pressure0 ～ 100
sensitive Pressure
Low positive pressure
Pressure
Pressure0 ～ 100
sensitive
Positive pressure
Pressure0 ～ 1000
sensitive Pressure
Positive pressure
Pressure0 ～ 1000
sensitive Pressure
Negative pressure
Pressure
0 ～－100
sensitive Pressure
Negative pressure
Pressure
0 ～－100
sensitive Pressure
Compound pressure
Pressuresensitive Pressure －100 ～ 100Compound pressure
Pressuresensitive Pressure －100 ～ 100
Low positive pressure
Pressure0 ～ 100
sensitive Pressure
Positive pressure
Pressure
Pressure0 ～ 1000
sensitive
Negative pressure
Pressure
Pressure
0～－100
sensitive
Compound pressure
Pressure
Pressure－100 ～ 100
sensitive

Indication status

20
20
20
20
20
20
20
20
20
20
20
20

Detailed status

On

A 25
A 25
A 25

Setting ofoperation mode

Response Standard
time
price (￥)

・Hysteresis mode・Window
comparator mode

B284SB-0□-1K□□P30
B284SB-J1-1K□□P30

Transmission signal error

LINK(Green) Flashing

ALM
(Red)

Consumption
current (mA) Connection* The dimensions are values only for the body.
*“B284SB-J1-1K□□P30” are types that occupy 16 points of input and output analog values in 10 bit binary.

＜ LED indication ＞
LEDsymbolGaugepressure(kPa)

Dimension
(mm)
Mass
(g)

Cylinder TypeTransmission signal reception

Off

disconnection and
No transmission signal (including
reverse connection of DP and DN)

On

Sensing level decrease* 1

Flashing

Slave unit voltage decrease

Off

Normal

LED indication unit

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

Alternate flashingIN(Orange)On(IN0)

B284SB-01-1K□□P30 Input ON
B284SB-02-1K□□P30 Input ON

On(IN1)

B284SB-02-1K□□P30 Input ON

Off

Input OFF

LINK
ALM

*2

*1: When alarm diagnosis function is enabled *2: B284SB-J1-1K□P30 does not have LED indication for IN.

Functional icon indication*See page 15 fordetails on function.

147

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKSENSOR＜ Characteristic diagram ＞ (Reference value)
・Pressure-AD value
1200

B284SB-□□-1KPLP30

1200
1000
AD value−Y (Digit)

AD value−Y (Digit)

1000

B284SB-□□-1KPP30

800
600
400

800
600
400

200

200

0

0

0

20

40
60
80
100
Applied pressure−X (kPa)120

Photoelectric Type
Laser Type
0

200
400
600
800 1000 1200
Applied pressure−X (kPa)

Fiber Type
Proximity Type

1200

B284SB-□□-1KNP30

1200

800
600
400
200
0

Pressure Type
Cylinder Type1000
AD value−Y (Digit)

AD value−Y (Digit)

1000

B284SB-□□-1KLP30

0

-20

-40

-60

-80

Photo Interrupter Type

800
600

Line Monitor

400

Small Display Unit

200

List of Specifications

0

-100

-150

-100

Applied pressure−X (kPa)

-50
0
50
100
Applied pressure−X (kPa)

150

・Pressure value-temperature characteristic
B284SB-□□-1KPLP30

120

1200
1000
Measured value−Y (kPa)

Measured value−Y (kPa)

100
80
60
40
20
0

B284SB-□□-1KPP30

800
600
400
200

0

20

40
25℃

60
0℃

80
100
60℃

0

120

0

Applied pressure−X (kPa)

B284SB-□□-1KNP30

150

600
800 1000 1200
0℃
60℃

B284SB-□□-1KLP30

100

-80
-60
-40
-20
0

400
25℃

Applied pressure−X (kPa)

Measured value−Y (kPa)

Measured value−Y (kPa)

-100

200

50
0
-50
-100

0.0

-20.0

-40.0
-60.0
-80.0
0℃
60℃
25℃
Applied pressure−X (kPa)

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring-100.0Maximum value
ThresholdMinimum value

-150
-150

Reading/
writing of
sensorsensitivity
setting

-100

-50
0
50
100
25℃
0℃
60℃
Applied pressure−X (kPa)

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

150

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

148

Slave Units(Sensor/Amplifier)

ASLINKSENSOR◆Cylinder type (amplifier relay type) (IP67) Cable with M12 connector/Cable, cylinder type

Photoelectric Type
Laser Type

BM-C27-DM9-3012-5050

Fiber Type

BM-C27-DM9-50-5050

B285SB-01-1K1

Proximity Type

Corresponding to cylinderround groove manufactured by SMC

Pressure Type

Photo Interrupter Type＜ Specifications ＞
O
NLine Monitor

O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
ThresholdDP/DN
disconnection

unnecessary

Minimum value

Dimension A: Amplifier 14×38×7.5
DP/DN
shortcircuit

20×4.5×4

Head

ID (address)
Duplicate/
Not set24V
drop

Dimension B: 10.4×22×11.3／: Not applicable －: Not determined

Small Display Unit

Number of
I/O points

List of Specifications

Input/
outputInput Output specifications

Model

Type

Consumption
current (mA) Connection

Dimension
(mm)
Mass
(g)

Cylinder Type2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

A 45

Max. 1.2ms

Open

A 40

Max. 1.2ms

Open

B 13

Max. 1.2ms

OpenTransmission I/O
side
side

8

Magnetic

Cylinderamplifier relay type
Cylinderamplifier relay type

Magnetic

Cylinder13

BM-C27-DM9-3012-5050

2

Magnetic

BM-C27-DM9-50-5050

2

B285SB-01-1K1

1

8Output max.
Input
resistance/ ON current (mA) Response Standard
1 point
Per 1
Per 1
time
price (￥)(kΩ)
point common*The dimensions are numerical values excluding the cable section.

＜ Outline Dimensional Drawings ＞

Unit: mm

Color:
Warm grayTransmission cable

CH1

11.3

XS5H

（300）

38
Red: DPBlack: DN

CH1Transmission cable20
6.7(Maximumsensitivity position)

（500）

CH0

φ
4

4

14

3

CH0

2.8

38

DN
1

7.5

4
2

M2.6
Slotted head set
screw
2.5
□1.5

N/C

UL style 2844
4-core×No.28AWG φ3.1 BlackUL style 2103 105° 300V
2-core×No.24AWG φ4.1 Black

11.3
20

7.5

DP

3

UL style 2844
4-core×No.28AWG φ3.1 Black
M2.6
Slotted head set
screw
2.5

φ
4

2

UL style 2103 105° 300V
2-core×No.24AWG φ4.1 BlackAKIN2-KAK-14462*

2.8

N/C

□1.5

1

ASLINKSENSOR BM-C27-DM9-50-5050

14

ASLINKSENSOR BM-C27-DM9-3012-5050

（500）

6.7
(Maximumsensitivity position)（500）

Core line
coating outer
diameter φ1.5

ASLINKSENSOR B285SB-01-1K1
M2.5×10
Slotted head set screw

4

10.4

5.1

11.25

22

（1000）
Flat shape cord
2X0.3SQ Red/black5
Maximum sensitivity position

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

149

AnyWireASLINK System

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

Slave Units(Sensor/Amplifier)

ASLINKSENSOR＜ LED indication ＞
Target modelLEDsymbol

BM-C27-DM9-□□□□-5050

Indication status

ALM
(Red)

LINK
ALM

LED
symbol

Detailed status
Transmission signal error

On
LINK(Green) Flashing

Indication status

Transmission signal reception(including disconnection and

No transmission signal reverse connection of DP and DN)

OnWhen input is ON: Sensing level decrease*
When input is OFF: Sensor cabledisconnection or short-circuit

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the ID(address) of this unit is duplicated or not set

CH0, 1 On(Green)Off

Detailed status
Transmission signal error

On
LINK(Green) Flashing

Off

LINK
ALM

B285SB-01-1K1

Target model

ALM
(Red)

LINK
ALM

Transmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease*

Flashing

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

On
IN
(Orange)
Off

Input ON (Rod detected)

Laser TypeFiber Type

Input ON

Proximity Type

Input OFF

Pressure Type

*When alarm diagnosis function is enabled

Input OFF (No rod detected)※アラーム診断機能有効時

CH0, 1 On
(Red)
Off

Photoelectric Type

Input ON* (Rod detected, unstable area)

Cylinder Type

B285SB-01-1K1

Photo Interrupter Type

Input OFF (No rod detected)
Line Monitor※アラーム診断機能有効時

MONITOR On(Orange)Off

Rod detectedLED
indication unit

No rod detected

Small Display Unit

*When alarm diagnosis function is enabled

List of Specifications

BM-C27-DM9-□□□□-5050<Amplifier part><Head part>LED
indication unitLED
indication unit

＜ Characteristic diagram ＞ (Reference value)*Data of BM-C27-DM9-□□□□-5050

・Detection distance characteristic
Target cylinder: CJP2 series φ6

Target cylinder: CU series φ16

200

200

200

50

-1

0

0
-50

1

2

3

Distance–X (mm)Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

150
100
50

-5

4

AD value-Y (Digit)

250

AD value-Y (Digit)

AD value-Y (Digit)

250

100

-2

Magnetic peak position

250

150

-3

300

Magnetic peak position

Magnetic peak position-4

Target cylinder: CQ2 series φ63

300

300

-4

-3

-2

-1

0

0
-50

1

2

3

4

150
100
50

-8

5

-6

Distance–X (mm)Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

-2

0

0
-50

2

4

6

8

Distance–X (mm)Interference Interference
countermeasure countermeasureunnecessary-4for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

AnyWireASLINK System

150

◆Photo Interrupter Type＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKSENSOR B297SB-01-1K40
26（1000）

9

19

25.4

5

2-φ3.819

Slave Units(Sensor/Amplifier)

ASLINKSENSOR

Setting port
2-φ3.8

Photoelectric Type7

11

Laser Type

16.7

Red: DPBlack: DNCore line coating outer diameter φ1.5

Fiber Type

6.4

*Contact our sales division
for attachment fittings.

Proximity Type
Pressure TypeBending-proof cable
2-core×No.24AWG (Black) φ4.5

Cylinder Type＜ Specifications ＞

Line Monitor
O
N

Small Display Unit

O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 25.4×7×26／: Not applicable －: Not determined

Consumption
Output max.
Input
Detection current (mA)resistance/ ON current (mA) Response StandardTypedistance Transmission I/O Connection
1 point
Per 1
Per 1
time
price (￥)
(mm)
(kΩ)
side
side
point common
2-wiretype
Photo
5
Transmission
Max. 1 cycle timeOpeninterrupter (Groove width) 11(non-insulation) A 27

Number of
I/O points Input/
outputInput Output specifications

List of Specifications

Model

1

B297SB-01-1K40

Dimension
(mm)
Mass
(g)

Photo Interrupter Type*The dimensions are numerical values excluding the cable section.

＜ LED indication ＞
LEDsymbolIndication statusOn
LINK(Green) Flashing

B297SB-01-1K40

Transmission signal reception(including disconnection andOff

No transmission signal reverse connection of DP and DN)

On

Sensing level decrease* 1

ALM(Yellow) Flashing

LINK
ALM

Detailed status
Transmission signal error

LED indication unit

Slave unit voltage decrease

Off

NormalAlternate flashing

When master unit detects that the
ID (address) of this unit is duplicatedor not set

LINK
ALM

Input ONOn
IN
(Orange)
Off

Input OFF*1 When alarm diagnosis function is enabled

Functional icon indication*See page 15 fordetails on function.

151

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

AnyWireASLINK System

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN line
disconnection disconnection
detection

DP/DN
shortcircuit

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

Slave Units(Sensor/Amplifier)

ASLINKMONITOR◆Line monitor handy type＜ Outline Dimensional Drawings ＞

Unit: mm27.5

ASLINKMONITOR ARW-SP

Setting port
69

Remote head outlet

Power switch

ARW-SP

115

Photoelectric Type
Laser Type

BACK

ENTER

HOME

Fiber Type
Proximity TypeTransmission
cable outlet

Pressure Type＜ Specifications ＞
O
N
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

Cylinder Type

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 115×69×27.5

Photo Interrupter Type

Consumption
current (mA)

Product
specifications

Model

Transmission side 24V side

5

Touch screen type line monitor

ARW-SP

Infrared data communications: Address, parameter setting
Transmission line / monitor, parameter setting

40*

Connection
4-wire type(insulation)

Dimension(mm)／: Not applicable －: Not determinedLine Monitor

Mass
(g)

Standard
price (￥)

A 150

Open

Small Display Unit
List of Specifications*Automatic switching between external supply DC24V power and AAA (cell) battery drive.

◆Small display unit Cable with M12 connector (IP67) / Cable＜ Outline Dimensional Drawings ＞

Unit: mm

ASLINKMONITOR B287-74DP01-□20（B287-74DP01-220）
2

300

1

38

4
1
2
3
4

B287-74DP01-220

N/C
DP
N/C
DN

17

3

φ14.9

44.7

XS5H (plug)
Color: BlackUL style 2103
2-core×No.24AWG (Black) φ4.1

（B287-74DP01-C20）
38

UL style 2103
2-core×No.24AWG (Black) φ4.1

17

Red: DPBlack: DN

7.5

B287-74DP01-C20（200）＜ Specifications ＞
O
F
F

Hi
LO
NG

Interference
countermeasure

Maximum value
Thresholdunnecessary

Minimum value

DP/DN
disconnection

DP/DN
shortcircuit

24V
drop

ID (address)
Duplicate/
Not setDimension A: 17×38×7.5／: Not applicable －: Not determined

Consumption
current (mA)

Product
specifications

Model

Transmission side 24V side

B287-74DP01-220

Optional address sensing level Display unit

6

B287-74DP01-C20

Optional address sensing level Display unit

6

Connection
2-wire type(non-insulation)
2-wire type(non-insulation)

Dimension
(mm)

O
N

Mass
(g)

Standard
price (￥)

A

21

Open

A

10

Open

*The dimensions are numerical values excluding the cable section.

Functional icon indication*See page 15 fordetails on function.

O
N
O
F
F

Hi
LO
NG

Sensing
level
monitoring

Maximum value
ThresholdMinimum value

Reading/
writing of
sensorsensitivity
setting

Sensorcable
disconnection
detection

Interference Interference
countermeasure countermeasureunnecessary

for transmission
line unnecessary

Transmission

DP/DN
shortcircuit

DP/DN line
disconnection disconnection
detection*

Transmission
line
short-circuit
detection

24V
drop

Transmission
circuit drive
power drop
detection

ID (address)
Duplicate/
Not setID (address)
redundant,
non-setting
detection

is a registered trademark of OMRON Corporation.

AnyWireASLINK System

152

Laser TypeFiber Type
Proximity Type＜ List of Specifications ＞
Number of
I/O points

Model
Set model
BS-H0117-PC-SET
Set model
BS-H0117-PC12-SET

Input Output

1
1
1
1
1

Set model
BS-H0117G-PC-SET

1

BS-H0217-1K

1

BS-H0217-3012

1

BS-H0217Ｇ-1K

1

BS-H0317-1K

1

BS-H0317-3012

1

BS-H0317Ｇ-1K

1
1

Set model
BS-L0117-PC-SET

1

BS-Ｌ0217-1K

1○: Mounted

Input/
outputspecifications
Transmission lightemitting (red light)
Transmission lightreceiving (red light)
Transmission lightemitting (red light)
Transmission lightreceiving (red light)
Transmission lightemitting (red light)
Transmission lightreceiving (red light)
Recurrent reflection(red light)
Recurrent reflection(red light)
Recurrent reflection(red light)
Spread reflection(red light)
Spread reflection(red light)
Spread reflection(red light)
Transmission
light emitting (red LD)
Transmission
light receiving (red LD)
Recurrent
reflection (red LD)

Consumption
current (mA)
Transmission I/Oside sideType

Photoelectric (IP67) 10
Photoelectric (IP67) 10
Photoelectric (IP67) 10
Photoelectric (IP67) 10
Photoelectric

10

Photoelectric

10(companystandard oil resistance IP67)(companystandard oil resistance IP67)

Photoelectric (IP67) 10
Photoelectric (IP67) 10
Photoelectric(companystandard oil resistance IP67)

10Photoelectric (IP67) 10
Photoelectric (IP67) 10(companystandard oil resistance IP67)

Photoelectric

10

Laser spot

7

Laser spot

8

Laser spot

10

Connection
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

Mass
(g)

Slave Units(Sensor/Amplifier)Photoelectric TypeASLINKSENSOR / ASLINKAMP
×: Not mounted ／: Not applicable － : Not determined
Output max.
SensorInput
resistance/ ON current (mA) Sensing sensitivity Senor cable Interference RAS
level
disconnection measure
1 point Per 1
Per 1 monitoring setting
function
read/write detection unnecessary(kΩ)
point common

33

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

22

○

○

○

○

Max. 2 cycle times

22

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

22

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

22

○

○

○

○

Max. 2 cycle times

33

○

○

○

○

Max. 2 cycle times

33

○

○

○*1

○

Max. 2 cycle times

33

○

○

○*1

○

Max. 2 cycle times

33

○

○

○*1

○

Max. 2 cycle times*1 With limitation

Number of
I/O points

Cylinder Type

Small Display Unit
List of Specifications

Type

Consumption
current (mA)
Transmission I/Oside side

Connection
4-wire type(insulation)
4-wire typeOutput max.
SensorInput
resistance/ ON current (mA) Sensing sensitivity Senor cable Interference RAS
level
disconnection measure
1 point Per 1
Per 1 monitoring setting
function
read/write detection unnecessary(kΩ)
point common

Response
time

LA-F1011

1

Fiber head (red light)

Base 1.9 25

21

○

○

○

○

Max. 2 cycle times

LB-F1011

1

Fiber head (red light)

○

○

○

○

Max. 2 cycle times

BA-F116-12

1

Fiber head (red light)

Extension 1.9 25 (insulation) 17
2-wire type
Base 11(non-insulation) 40

○

○

○

○

Max. 2 cycle times

BA-F1161

Fiber head (red light)

47

○

○

○

○

Max. 2 cycle times

B289SB-01AF-CAM20-V

1

Fiber head (red light)

Base 11
Base 11

14

○

○

○

○

Max. 2 cycle times

B289SB-01AF-CAS-V

1

Fiber head (red light)

Extension 11

9

○

○

○

○

Max. 2 cycle times

Number of
I/O points

Input/
outputspecifications

Model

153

Input/
outputspecifications

Input Output

Input Output

BS-K1117-M08-3012

1

BS-K1117-M12-3012

1

BS-K1117-M18-3012

1

BS-K1117-M30-3012

1

BS-K1117-M08-1K

1

BS-K1117-M12-1K

1

BS-K1117-M18-1K

1

BS-K1117-M30-1K

1

BS-K1117S-M12-3012

1

BS-K1117S-M18-3012

1

BS-K1117S-M30-3012

1

BS-K1117S-M12-1K

1

BS-K1117S-M18-1K

1

BS-K1117S-M30-1K

1

BS-K1217-M08-3012

1

BS-K1217-M12-3012

1

BS-K1217-M18-3012

1

BS-K1217-M30-3012

1

BS-K1217-M08-1K

1

BS-K1217-M12-1K

1

BS-K1217-M18-1K

1

BS-K1217-M30-1K

1Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction

AnyWireASLINK SystemType2-wire type(non-insulation)
2-wire type(non-insulation)
2-wire type(non-insulation)

Consumption
current (mA)
Transmission I/Oside side

Proximity M8
13.8
Standard type
Proximity M12
8.4
Standard type
Proximity M18
8Standard type
Proximity M30
8.2
Standard type
Proximity M8
13.8
Standard type
Proximity M12
8.4
Standard type
Proximity M18
8Standard type
Proximity M30
8.2
Standard type
Proximity M12
Sputter ready type 8.4
Proximity M18
Sputter ready type 8
Proximity M30
Sputter ready type 8.2
Proximity M12
Sputter ready type 8.4
Proximity M18
Sputter ready type 8
Proximity M30
Sputter ready type 8.2
Proximity M8
Non-shield type 14.3
Proximity M12
6.8
Non-shield type
Proximity M18
6.7
Non-shield type
Proximity M30
6.5
Non-shield type
Proximity M8
Non-shield type 14.3
Proximity M12
6.8
Non-shield type
Proximity M18
6.7
Non-shield type
Proximity M30
6.5
Non-shield type

Connection

Mass
(g)

Line Monitor

Model

Mass
(g)

Pressure Type

Photo Interrupter Type

Responsetime

2-wire type(non-insulation) 21
2-wire type(non-insulation) 31
2-wire type(non-insulation) 44
2-wire type(non-insulation) 107
2-wire type(non-insulation) 28
2-wire type(non-insulation) 41
2-wire type(non-insulation) 54
2-wire type(non-insulation) 117
2-wire type(non-insulation) 31
2-wire type(non-insulation) 44
2-wire type(non-insulation) 107
2-wire type(non-insulation) 41
2-wire type(non-insulation) 54
2-wire type(non-insulation) 117
2-wire type(non-insulation) 20
2-wire type(non-insulation) 29
2-wire type(non-insulation) 38
2-wire type(non-insulation) 90
2-wire type(non-insulation) 27
2-wire type(non-insulation) 37
2-wire type(non-insulation) 45
2-wire type(non-insulation) 96

Output max.
SensorInput
resistance/ ON current (mA) Sensing sensitivity Senor cable Interference RAS
level
disconnection measure
1 point Per 1
Per 1 monitoring setting
function
read/write detection unnecessary(kΩ)
point common

Response
time

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

＜ List of Specifications ＞
Model

Input Output

Input/
outputspecifications○: Mounted
Type

Consumption
current (mA)
Transmission I/Oside side

Proximity M12
Full stainless steel body type 4.7
Proximity M18
Full stainless steel body type 4.7
Proximity M30
Full stainless steel body type 4.7
Proximity M12
Full stainless steel body type 4.7
Proximity M18
Full stainless steel body type 4.7
Proximity M30
Full stainless steel body type 4.7
Proximity M12
Chemical-capable type 6.9
Proximity M18
Chemical-capable type 7.0
Proximity M30
Chemical-capable type 7.0
Proximity M12
Chemical-capable type 6.9
Proximity M18
Chemical-capable type 7.0
Proximity M30
Chemical-capable type 7.0
Proximity M12Polyarylate body type 6.9
Proximity M18
Polyarylate body type 7.0
Proximity M30
Polyarylate body type 7.0
Proximity M12Polyarylate body type 6.9
Proximity M18
Polyarylate body type 7.0
Proximity M30
Polyarylate body type 7.0
Proximity M12
All metal detection type 6.9
Proximity M18
All metal detection type 7.0
Proximity M30
All metal detection type 7.0
Proximity M12
All metal detection type 6.9
Proximity M18
All metal detection type 7.0
Proximity M30
All metal detection type 7.0
Proximity φ4
6.3
Amplifier relay type
Proximity φ5.4
6.5
Amplifier relay type
Proximity M4
5.9
Amplifier relay type
Proximity M5
6.4
Amplifier relay type
Proximity φ4
6.3
Amplifier relay type
Proximity φ5.4
6.5
Amplifier relay type
Proximity M4
5.9
Amplifier relay type
Proximity M5
6.4
Amplifier relay typePressure(Low positive pressure) 20
Pressure(Low positive pressure) 20
Pressure
20(Positive pressure)Pressure
20(Positive pressure)Pressure
20(Negative pressure)Pressure
20(Negative pressure)Pressure(Compound pressure) 20
Pressure(Compound pressure) 20
Pressure(Low positive pressure) 20
Pressure
20(Positive pressure)Pressure
20(Negative pressure)Pressure(Compound pressure) 20
Cylinderamplifier relay type 8
Cylinderamplifier relay type 8

BS-K1117M-M12-3012

1

BS-K1117M-M18-3012

1

BS-K1117M-M30-3012

1

BS-K1117M-M12-1K

1

BS-K1117M-M18-1K

1

BS-K1117M-M30-1K

1

BS-K1117Ｃ-M12-3012

1

BS-K1117Ｃ-M18-3012

1

BS-K1117Ｃ-M30-3012

1

BS-K1117Ｃ-M12-1K

1

BS-K1117Ｃ-M18-1K

1

BS-K1117Ｃ-M30-1K

1

BS-K1118-M12-3012

1

BS-K1118-M18-3012

1

BS-K1118-M30-3012

1

BS-K1118-M12-1K

1

BS-K1118-M18-1K

1

BS-K1118-M30-1K

1

BS-K4117-M12-3012

1

BS-K4117-M18-3012

1

BS-K4117-M30-3012

1

BS-K4117-M12-1K

1

BS-K4117-M18-1K

1

BS-K4117-M30-1K

1

BM-K1117G-S04-3012

1

BM-K1117G-S05-3012

1

BM-K1117G-M04-3012

1

BM-K1117G-M05-3012

1

BM-K1117G-S04-1K

1

BM-K1117G-S05-1K

1

BM-K1117G-M04-1K

1

BM-K1117G-M05-1K

1

B284SB-01-1KPLP30

1

B284SB-02-1KPLP30

2

B284SB-01-1KPP30

1

B284SB-02-1KPP30

2

B284SB-01-1KNP30

1

B284SB-02-1KNP30

2

B284SB-01-1KLP30

1

B284SB-02-1KLP30

2

B284SB-J1-1KPLP30

16

B284SB-J1-1KPP30

16

B284SB-J1-1KNP30

16

B284SB-J1-1KLP30

16Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Electromagnetic
induction
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive
Pressuresensitive

BM-C27-DM9-3012-5050

2

Magnetic

BM-C27-DM9-50-5050

2

Magnetic

B285SB-01-1K1

1Magnetic

Cylinder13

B297SB-01-1K40

1Transmission

Photo interrupter

11

Connection

Mass
(g)

Number of
I/O points

2-wire type(non-insulation) 32
2-wire type(non-insulation) 47
2-wire type(non-insulation) 107
2-wire type(non-insulation) 39
2-wire type(non-insulation) 55
2-wire type(non-insulation) 115
2-wire type(non-insulation) 24
2-wire type(non-insulation) 34
2-wire type(non-insulation) 68
2-wire type(non-insulation) 31
2-wire type(non-insulation) 40
2-wire type(non-insulation) 76
2-wire type(non-insulation) 23
2-wire type(non-insulation) 30
2-wire type(non-insulation) 62
2-wire type(non-insulation) 30
2-wire type(non-insulation) 38
2-wire type(non-insulation) 70
2-wire type(non-insulation) 31
2-wire type(non-insulation) 42
2-wire type(non-insulation) 98
2-wire type(non-insulation) 37
2-wire type(non-insulation) 49
2-wire type(non-insulation) 105
2-wire type(non-insulation) 22
2-wire type(non-insulation) 23
2-wire type(non-insulation) 22
2-wire type(non-insulation) 23
2-wire type(non-insulation) 30
2-wire type(non-insulation) 31
2-wire type(non-insulation) 30
2-wire type(non-insulation) 31
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 25
2-wire type(non-insulation) 45
2-wire type(non-insulation) 40
2-wire type(non-insulation) 13
2-wire type(non-insulation) 27

×: Not mounted ／: Not applicable － : Not determined
Output max.
SensorInput
resistance/ ON current (mA) Sensing sensitivity Senor cable Interference RAS
level
disconnection measure
1 point Per 1
Per 1 monitoring setting
function
read/write detection unnecessary(kΩ)
point common

Response
time

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms

○

○

×

○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 10ms○○○

Max. 1.2ms

○

○

○

Max. 1.2ms

○

○

○

Max. 1.2ms

○

×

○

Max. 1 cycle times

AnyWireASLINK System

Slave Units(Sensor/Amplifier)

ASLINKSENSOR / ASLINKAMP

Photoelectric Type
Laser TypeFiber Type
Proximity Type
Pressure Type
Cylinder Type
Photo Interrupter TypeLine Monitor
Small Display Unit
List of Specifications

154

155

AnyWireASLINK System

Third Party

Third party products with AnyWireASLINK functions built-in
Manifold driver compatible
with AnyWireASLINK manufactured by SMC ・・・ 157
FA equipment-linked
screwdriver manufactured by NITTO KOHKI ・・・ 158

156

Manifold driver compatible with AnyWireASLINK (SI unit) manufactured by SMC

Third Party◆EX180-SAW1-X237

Manifold driver
FA equipment-linked
screwdriver＜ Overview ＞
Valve manifold (SI unit) that can be connected to AnyWireASLINK◇Functions as AnyWireASLINK 4-wire type (insulation) slave unit
◇Number of output points: 32 points◇Output type : NPN open collector◇Applicable valve series : SJ series, S0700 series<Features of SJ series>
・Body width of 7.5 mm (SJ2000) and 10 mm (SJ3000) is available and various kinds ofvalves can be mounted.
・Vacuum breaker with throttle valve is available and vacuum adsorption and vacuum
break can be controlled.
・Easy to add or remove by connecting valves with a connector.
・The reducing valve block located inside the manifold reduces supplied pressure,enabling two different pressures to be used by one manifold.

SJ series＜ Specifications ＞／: Not applicable －: Not determined

Number of
I/O points

Model

Input Output

MethodTransmission
side

I/O
side

Tr output

NPN

13

*1

32

EX180-SAW1-X237

Consumption
current (mA)

Input/
outputspecifications

Connection

Mass
(g)

4-wire type (insulation) 100

Standard
price (￥)
Sold by SMC*1 This differs depending on the load to be connected.

＜ Example of configuration ＞
Mitsubishi Graphic Operation Terminal
GOT1000/GOT2000 series

MELSEC-Q
AnyWireASLINKMaster interface

SMC Corporation SJ series
Manifold
AnyWireASLINK transmission line
SI UNIT

SI UNITASLINKSENSOR
Pressure type

ASLINKTERMINAL
8-point terminal (Output)
ASLINKAMP Analog input (insulation type between channels)
LINK
V
mA
ALM

LINK
V
mA
ALM

ASLINKSENSOR
Proximity type

AnyWireASLINK
Terminator (BT0)For product details and purchase, contact the following:[Contact] SMC Corporation

Akihabara UDX15F, 4-14-1, Sotokanda, Chiyoda-ku, Tokyo 101-0021 JAPANCustomer service

157

AnyWireASLINK System

Toll-free number 0120-837-838 / http://www.smcworld.com

◆Electric screwdriver compatible with AnyWireASLINK delvo＜ Application ＞
Using screwdrivers with different torques to tighten multiple kinds of screws for production◇Prompt recovery from disconnection between sequencer and screwdriver(Prompt identification of disconnection using AnyWireASLINK disconnection detection function)

Third Party

FA equipment-linked screwdriver manufactured by NITTO KOHKI(Electric screwdriver compatible with AnyWireASLINK)◇Easy to expand or change equipment(Easy to perform additional works using AnyWireASLINK Sho-Haisen function)◇Prevention of incorrect screwdriver selection

Manifold driver(Using electric screwdrivers equipped with selection LED display)

DLV7000/8000-ASL series◇Prevention of incorrect screw selection(Screws selected by POKAYOKE terminal)

FA equipment-linked
screwdriver◇Managing traceability of length/tightening completion of each screw◇Prompt analysis of each worker’s error and prompt improvement◇Easy to connect to other equipment(Expansion is possible by using various sequencer units)
DLV7100/7200/8100/8200-ASL series＜ Specifications ＞◇Various models different in starting method, torqueand number of times of rotations are available
for selection.

DLV30/45/70-ASL series

Model

Lever start

DLV30LL-ASL(DJE)

DLV30SL-ASL(DJE)

DLV30HL-ASL(DJE)Push start

DLV30LP-ASL(DJE)

DLV30SP-ASL(DJE)

DLV30HP-ASL(DJE)

Lever start

DLV45LL-ASL(DKE)DLV45SL-ASL(DKE)

DLV70LL-ASL(DKE)

Push start

DLV45LP-ASL(DKE)DLV45SP-ASL(DKE)

DLV70LP-ASL(DKE)DLV7100 series

Lever start

DLV7120-ASL(EJN) DLV7130-ASL(EJN) DLV7140-ASL(EJN)

DLV8100 series

Push start

DLV8120-ASL(EJN) DLV8130-ASL(EJN) DLV8140-ASL(EJN) DLV8150-ASL(EKN)

DLV7200 series

Lever start

DLV7220-ASL(EJN) DLV7231-ASL(EJN) DLV7241-ASL(EJN) DLV7251-ASL(EKN)

DLV8200 series

Push start

DLV8220-ASL(EJN) DLV8231-ASL(EJN) DLV8241-ASL(EJN) DLV8251-ASL(EKN)

DLV7000 series

Lever start

DLV7020-ASL(EMN)

DLV7030-ASL(EMN)

DLV7031-ASL(EMN)

DLV8000 series

Push start

DLV8020-ASL(EMN)

DLV8030-ASL(EMN)

DLV8031-ASL(EMN)

DLV30 series
DLV45/70 series―* All models are sold by NITTO KOHKI.

＜ Example of configuration ＞
Mitsubishi Graphic Operation Terminal
GOT1000/GOT2000 series

Door type POKAYOKE terminal

MELSEC-Q
AnyWireASLINKMaster interface

AnyWireASLINK transmission line

Signal tower

ASLINKER
2-point terminal (Output)
LINK
OUT0
OUT1
ALM

LINK
OUT0
OUT1
ALM

Electric screwdrivers

OUT0
OUT1

OUT0
OUT1

AnyWireASLINK
Terminator (BT0)

Buzzer

For product details and purchase, contact the following:[Contact] NITTO KOHKI CO., LTD. 2-9-4, Nakaikegami, Ohta-ku, Tokyo 146-8555 JAPANTEL 03-3755-1111 / http://www.nitto-kohki.co.jp

AnyWireASLINK System

158

159

AnyWireASLINK System

Appendix

Consumption current calculation(How to calculate the number of connectable units) ・・・ 161
Address Writer・・・ 163

Correspondence Table of Applicable Connectors ・・・ 165

160

Consumption current calculation for AnyWireASLINK(How to calculate number of connectable units)

Appendix■Power supply to AnyWireASLINK system(1) How to supply power to slave unit
Connect 24V DC external supply power to the master unit.
Consumption current of the internal control circuits of all slave units and the external load current connected to the slave unitof the 2-wire (non-insulation) type are completely supplied from 24V DC external supply power connected to the master unit.

(2) Applicable range of power supply by transmission line (DP/DN)
Consumption current of the system necessarily meets all conditions of the following ① to ③ for one master unit.
Consumption
current calculation

Condition

Calculating formulaContents

Address Writer

Ihin: Consumption current of input unit of 2-wire (non-insulation) type
Iho: Consumption current of output unit of 2-wire (non-insulation) typeIzdin: Consumption current of input unit of 4-wire (insulation) typeIzdo: Consumption current of output unit of 4-wire (insulation) typem: Number of connected input units of 2-wire (non-insulation) typen: Number of connected output units of 2-wire (non-insulation) typep: Number of connected input units of 4-wire (insulation) typeq: Number of connected output units of 4-wire (insulation) type

Applicable
Connectors

I(A)=(Ihin×m)+(Iho×n)+(Izdin×p)+(Izdo×q)①≦Maximum value oftransmission line supply current②③

Vm(V)－∆V(V) ≧ 20V

Vm: Power supplied to master unit

Vm(V)－∆V (V)≧Lower limit of connected load allowable voltage range(a) Explanation of condition ① * Internal consumption current of each unit means “transmission side consumption current.”- Constants related to slave unit of 2-wire (non-insulation) type (Ihin, Iho)
In the slave unit of the 2-wire (non-insulation) type, current necessary for the internal control circuit and connected load issupplied from the transmission line (DP/DN).
Ihin(A) = Consumption current of input unit of 2-wire (non-insulation) type= Internal consumption current of input unit of 2-wire (non-insulation) type + connected load (3-wire type sensor)
consumption current × number of points
Iho(A) = Consumption current of output unit of 2-wire (non-insulation) type= Internal consumption current of output unit of 2-wire (non-insulation) type + connected load consumption current × number of points■2-wire (non-insulation) type terminal configuration
Slave unit of 2-wire (non-insulation) type

Master unit
24V 0VInternal control circuit
Power source
generation

DP DN
DP DN

24VL 0VL

0

1

……

n

24V 0V

24V DC
external supply
power

Connected load

- Terminals for 24VL, 0VL of the slave unit of
2-wire (non-insulation) type are terminals for
power supply of connected load.
- See the manual of each slave unit for
consumption current of the slave unit of
2-wire (non-insulation) type.

- Constants related to slave unit of 4-wire (insulation) type (Izdin, Izdo)
In the slave unit of the 4-wire (insulation) type, only current necessary for internal control circuit is supplied from the transmission
line (DP/DN) and current necessary for connected load is supplied from 24V DC external supply power.
Izdin(A) = Internal consumption current of input unit of 4-wire (insulation) typeIzdo(A) = Internal consumption current of output unit of 4-wire (insulation) type■4-wire (insulation) type terminal configuration
Master unit
24V 0V

24V 0V

24V DC
external supply
power

Slave unit of 4-wire (insulation) typeInternal control circuit
……

DP DN

DP DN

Load drive circuit (photo coupler insulation)……
24V 0V01
n24V 0V

24V DC
external
supply power

Connected load

- In the slave unit of 4-wire (insulation) type,consumption current of connected load is nota current limit condition of the AnyWireASLINK
system.
- See the manual of each slave unit for
consumption current of the slave unit of
4-wire (insulation) type.

*Master unit = ASLINKMASTER, Slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKMAP, ASLINKSENSOR)

161

AnyWireASLINK System

Consumption current calculation for AnyWireASLINK- Transmission line supply current (I(A))
Transmission line supply current of AnyWireASLINK system is obtained by the following formula.
I(A) = (Ihin×m)+(Iho×n)+(Izdin×p)+(Izdo×q)
Number of connected units: m, n, p, q (units)

Appendix(How to calculate number of connectable units)- Maximum value of transmission line supply current
See the “DP-DN allowable supply current” on page 14 for the maximum value of the transmission
line supply current.
Consumption
current calculation(b) Explanation of conditions ②, ③

Address Writer- Vm: Voltage supplied to master unit

Applicable
Connectors

Voltage: 21.6 to 27.6V DC (24V DC -10 to +15%), ripple voltage 0.5Vp-p or less
Recommended voltage: 26.4V DC (24V DC+10%)- ∆V(V): Voltage drop between lines- ∆V(V) = Transmission line supply current I(A) × line path resistance R(Ω)
Line path resistance R(Ω) = Electric wire length (m) ×conductor resistance (Ω/m) ×2- Size 1.25mm2→ Conductor resistance 0.015Ω/m- Size 0.75mm2→ Conductor resistance 0.025Ω/m(c) Example of calculation
An example of confirming whether a system under the following condition can be built
at a total length 100m is shown below.
[Condition]- Slave unit of 2-wire (non-insulation) type (input ASLINKER)
Number of input/output points: 2 points
Unit consumption current: 15.4mA
Number of units: 24 units- Connected load (3-wire type sensor)
Sensor consumption current: 13mA
Number: 2 / unit
Power voltage: 24V DC±10%- Size of transmission line (DP/DN)
Size: 1.25mm2- Supply power of master unit
Power voltage: 24V DC[Calculation result]
Condition ① (Ihin (A) ×m) = I(A)≦Maximum value of transmission line supply current(0.0154+(0.013×2)) ×24 = 0.9936A≦1A→ This meets the condition.
Condition ② Vm(V) － ∆(V)≧20V
24-(0.9936×100×0.015×2)≒24－2.981 = 21.019V≧20V → This meets the condition.
Condition ③ Vm(V) －∆(V)≧Lower limit of connected load allowable voltage range
Lower limit of connected load allowable voltage range = 24－24×0.1 = 21.6V
21.019V<21.6V→ This does not meet the condition.

It is confirmed that no system can be built according to the calculation results of the above① to ③.
If the supply power voltage to the master unit is adjusted to be higher, the allowable
voltage 1A will be exceeded. Therefore, consider rebuilding such as increasing the system
to diversify the power load or replacing with a slave unit (input ASLINKER) of a 4-wire type(insulation) to diversify the power.

*Master unit = ASLINKMASTER, Slave unit = various terminals (ASLINKER, ASLINKTERMINAL, ASLINKMAP, ASLINKSENSOR)

AnyWireASLINK System

162

Appendix

Address Writer
The address writer “ARW-04” is a tool for setting and checking ID (address) No. and sensitivities of various sensors
by infrared ray communication.
Fits comfortably in the palm of a hand making it very convenient on-site. Strap, etc., to prevent drop can beinstalled on the ring on the side.
When using ARW-04 in AnyWireASLINK,
use one in which the firmware version is “04-1.01 or higher.”■Display of firmware version
Version is displayedwhen POWER is on.

Consumption
current calculation
Address Writer

Remote head
ARW-RH appearance

Address writer
ARW-04 appearance“Ver.*.**” is indicatedon this label.

Applicable
Connectors

Front

Back

■Image of setting[Setting on narrow locations][Set on body]

If a fitting place for ASLINKER and ASLINKSENSOR
is crowded, and it is difficult to pass ARW-04 over,a remote head (ARW-RH: Separately sold) is available.

Remote head (ARW-RH)■Address writer operation items
Modes which can be set by ARW-04 as follows.
PurposeProcedureName of each part of ARW-04
Mode selected (function)

Press POWER switch
while pressing
SELECT switch

ARW-04 initial setting

Light emitting/receiving
part position (yellow part)

Operation modeindication lamp

Maximum point number setting mode
Maximum parameter number setting mode

POWER indication lamp

Decimal number or hexadecimal number display setting mode
Parameter set value automatic carry presence/absence setting mode

Comment display part
(7 segment 6 digits)

Ring for strap

Address writer mode
Teaching

Direct update

EX modeAddress reading

Direct reading

READ mode

Power reset update

WRITE mode

Direct update

DIRECT WRITE mode

Direct reading

READ mode

Power reset update

WRITE mode

Direct update

DIRECT WRITE mode

Address writing
Parameter reading
Parameter writing■Positioning guideline at timeof reading and writing[Seen from above]

Setting port

RH (remote head)

SELECT switch

connection connector (side)
POWER (CLEAR) switch

UP button

R button

L button

SET switch
DOWN button■How to write, readTransmission signal is required for sensor sensitivity setting, address writing
and reading. Set them with transmission signal supplied to the transmission
line (DP, DN) of the terminal.

- In case of 2-wire (non-insulation) terminal
Light emitting and receiving partApprox.
20 degrees Up to approx. 20mm

Transmission
signalRed: DPASLINKMASTER
Black: DN

DC24V[Seen from side]- In case of 4-wire (insulation) terminal

Light emitting and receiving part

Setting port

Approx.
20 degrees

Transmission
signalRed: DPASLINKMASTER
Black: DN

DC24VGreen: 24V(Brown)White: 0V

When writing, confirm that power (transmission signal in case of 2-wire (non-insulation) type) is supplied to the target unit.
In addition, after writing all, confirm safety and reset the power (same as above) of the target unit, and then update the writing result.
If written outside of the setting range, an error message “E-0303” is displayed.

163

AnyWireASLINK SystemAddress Writer■Teaching by address writer

Appendix* This is a case example of ASLINKSENSOR (photoelectric transmission type),
however, ASLINKAMP is also similarly equipped with the teaching function.

①States of “SET ON (work presence)” and “SET OFF (work absence)” can be indicated by the teaching functionof the address writer (ARW-04).

ASLINKSENSOR(Light emitting side)

ASLINKSENSOR(Light receiving side)

SET ONInfraredray

Work

In case of “work presence”

Address writer

Set work, and command “SET ON” to the light receiving side.

Determine the position of the sensor so that the lightemitting side and light receiving side are facing eachother, and carry out wiring and check operations.

F
SET OF
Infraredray

In case of “work absence”

Consumption
current calculation
Address Writer
Address writer

Command “SET OFF” to the light receiving side without work.

Applicable
Connectors②The sensing level range is determined by the taught value, and drop of sensing level can be detected by setting
an alarm value for the range.
100

100

Work absence (OFF)80

50Threshold of default

Alarm judgment value (upper limit)
When the sensing
level is lowered50

Sensing level lowered

20
0

There is no problem with
ON/OFF, however, the sensing
state is deteriorated comparedto the state at time of teaching.

Alarm judgment value (lower limit)

0Work presence (ON)

Numerical expression is optimized by teaching, and thesensing level and threshold are automatically set.

When the sensor axis (optical axis) is deviated by vibration or it is within therange of alarm judgment value for a certain time due to contamination, it isregarded as “sensing level drop.”■Desktop address writer
Addresses and parameters can be set to the terminal, teaching operation can be performed and the set contents can be confirmed even in an environment without a controller (address setting and teaching are possible only when infrared communication isused). Two types (LP connector connection and push terminal) of transmission signal
output and power supply terminals are provided, and various settings are possible justby connecting the terminal to a desktop address writer.
In addition, the same head connection connector as ARW-04 is also equipped, whichallows reading and writing by infrared communications using the remote head.
[Connection example][Difference between address writer ARW-04 and desktop address writer ARW-D04]
Address setting
Parameter setting
Teaching

Infraredcommunications

Compatible withremote head

Master-less settingof address, etc.

Reading and writingof parameters usingtransmission line

Button operation
when specifying
numerical value

Writing timing

Drive powersourcePortability

Remote head
connection connector(Sold separately)

ARW-04

○

○

○

×

×

Cycle values
by direction
buttonWriting after
power isreset/
immediatewriting

Dry batteries(Two AAAbatteries)◎

ARW-D04

○

○

○

○

○

Mechanicalnumerical
keypadImmediatewriting

AC adaptor
POWER

Transmission line
(LP connector
connection)

POWER

Transmission line
(Push terminal
connection)

LINK

READ

WRITE

EX

IR

IN

OUT

7
E

4

DATA

MODE

0V

DP

DN

5

D

2

0

Mode
SelectA

Light emitting/receiving section(Infrared ray)

8

1

B
24V

External appearance ofdesktop address writer
ARW-D04

9
F

6

CLR

Dec
/Hex

3

IR

Shif tSet

C

AC adaptor
Dry batteries(When driving(Four AAbybatteries)
dry batteries)△

See the separate Product Manuals for the details of ARW-04 and ARW-D04 to understand the functions for use.

AnyWireASLINK System

164

Consumption
current calculation

ASLINKER(SmartLINKER)

φ1.1

Trunk
line

Targetproduct
LP
connector

BL2LN87SB-02D□-CC20

4-wireApplicable
Connectors

B281□B-02U□-CC20

When connecting to 2-wire
LP2-PWH-10P
2-wire 24 φ1.5
When connecting to 4-wire
LP4-WW-10P

43(Cable type)BL287□B-02F□-CC20
ASLINKER(M12 connector type)
ASLINKTERMINAL(Small terminal block terminal,
compatible with cable type3-wire type sensor)

BL296□B-□□F□-V50
BL296□B-□□F□-3-V50
BL296□B-□□F□-11-V50

ASLINKTERMINAL(Integrated small 4-point terminal)

BL296□B-04F□-4A-20

ASLINKTERMINAL(Integrated small 8-point terminal)

BL296□B-08F□-4-20

ASLINKTERMINAL(Integrated small 16-point terminal)

BL296□B-16F□-4A-20

ASLINKTERMINAL(Power distribution unit)

BL296-0□PW4ASLINKTERMINAL(Small 8-point terminal)

BL296□B-08F□-20

ASLINKAMP(Fiber type (with 7 segment display))LE
connector

4-wire 23 φ1.4

47

When connecting to 2-wire
LP2-PWH-10P
2-wire 24 φ1.5
When connecting to 4-wire
LP4-WW-10P

49
53

4-wire 23 φ1.4

LP4-WW-10P

4-wire 23 φ1.4

LP4-WW-10P

4-wire 23 φ1.4

LP4-WW-10P

φ1.0
EP4-OR-8P

LP4-WW-10P

61

EP4-OR-8P

64
65

LA-F1011

105 4-wire

φ1.1

EP4-YE-8P

BA-F116
B289SB-01AF-CAM20-V

107
109 2-wire

φ1.5

EP4-OR-8P

ASLINKAMP(Analog input unit
(7 segment display equipped type))

LA-A12W

75

LA-A1AW77

ASLINKAMP(Analog output unit
(7 segment display equipped type))

LA-D□12W

79

LA-D□1AW81

ASLINKAMP(Fiber type)

165

45

B280□B-02U□-C1220

Targetproduct

LP4-WW-10P

Address Writer

ASLINKER

Trunk
line

AnyWireASLINK System

4-wire24 φ1.1

4-wireφ1.1When connecting to 2-wire
LP2-PWH-10P
When connecting to 4-wire
LP4-WW-10P

I/O sidecore line coat outline

37

When connecting to 2-wire
LP2-PWH-10P
2-wire 24 φ1.5
When connecting to 4-wire
LP4-WW-10P

B2N87SB-02D□-CC20

Transmission sidecore line coat outline

Model<When connected to LP connector> <When connected to LE connector>
Transmission side
Transmission side
LP connector
EP connector

Transmission sideconnection

Product

Transmission side
AWG／: Not applicable

Listing page

Appendix

Correspondence table of AnyWireASLINK and applicable connectors

EP4-YE-8P

EP4-YE-8P

ASLINKSENSOR(Photoelectric type)

BS-H0□17-1K□
BS-H0□17G-1K□

ASLINKSENSOR(Laser spot type)

BS-L0□17-1K

ASLINKSENSOR(Proximity type)

BS-K1117□-M□-1K

ASLINKSENSOR(Proximity type)

BS-K1217-M□-1K

ASLINKSENSOR(Proximity type)

BS-K1117C-M□-1K

ASLINKSENSOR(Proximity type)

BS-K1118-M□-1K

ASLINKSENSOR(Proximity type)

BS-K4117-M□-1K

ASLINKSENSOR(Proximity type)BM-K1117G-□□-1K

ASLINKSENSOR(Pressure type)BM-C27-DM9-50-5050

ASLINKSENSOR(Cylinder type)

B285SB-01-1K1

ASLINKSENSOR(Photo interrupter type)

B297SB-01-1K40

BT0-C

TargetproductLE
connector

I/O sidecore line coat outline

Transmission sidecore line coat outline

LPconnector

Trunk
line

101

Address Writer
Applicable
Connectors

113
117
125
EP4-OR-8P

121

24

129
133
φ1.5

2-wireWhen connecting to 2-wire
LP2-PWH-10P
When connecting to 4-wire
LP4-WW-10P

137
141

EP4-BL-8P
24

24

EP4-OR-8P

149
22
151

24

152 2-wire

24 φ1.5

BT0

Terminator for
AnyWireASLINK

Targetproduct

Consumption
current calculation

BT0
B287-74DP01-C20
ASLINKMONITOR(Small display unit)

Trunk
line

89
93
97

B284SB-0□-1K□P30
B284SB-J1-1K□P30 147
B284SB-0□-1KPLP30

ASLINKSENSOR(Cylinder type)Transmission side
AWG

Model

Transmission sideconnection

Product

Listing page／: Not applicable<When connected to LP connector> <When connected to LE connector>
Transmission side
Transmission side
LP connector
EP connector

Appendix

Correspondence table of AnyWireASLINK and applicable connectors

22

2-wireWhen connecting to 2-wire
LP2-PWH-10P
When connecting to 4-wire
LP4-WW-10P

EP4-OR-8P

When connecting to 2-wire
LP2-BK-10P
19 φ2.3
When connecting to 4-wire
LP4-OR-10P
When connecting to 2-wire
LP2-PWH-10P
24 φ1.5
When connecting to 4-wire
LP4-WW-10P

EP4-OR-8P

AnyWireASLINK System

166

Bitty series catalog

DB A20 series catalog

DB A40 series catalog

Energy monitoring energy
saving support catalog

Mitsubishi Electric Corporation Product catalog

ASLINKPOKAYOKE catalog

POKAYOKE catalog

MITSUBISHI & Anywire
L (NA) 08198

Contact□ Contact by mail□ Contact by website

Sensor solution
iQ Sensor Solution
L (NA) 08253

info_e@anywire.jp
http://www.anywire.jp

Price, specifications and design may be subject to change without notice.
<Warranty>◇Warranty period
The warranty on the delivered Product shall continue to be effective for one (1) year after the delivery thereof to a location designated by theoriginal owner.
◇Scope of warranty
Should a defect occur in any part of the Product during the foregoing warranty period when it is used normally in accordance with thespecifications described in this User's Manual, the Company shall replace or repair the defect free of charge, except when it arises as a result of:(1) Misuse or abuse of the Product by the owner;(2) Fault caused by reason of other than the delivered Product;(3) The unauthorized modification or repair of the Product by any person other than the Company's personnel;(4) Any unusual force of nature, disaster or other cause beyond the Company's control.
The term "warranty," as used herein, refers to the warranty applicable to the delivered product alone. The Company shall not be liable forconsequential or incidental damage resulting from any malfunction.
◇Repair at cost
After the expiration of the warranty period, the owner shall be responsible for all costs and expenses incurred for the troubleshooting andrepair of the Product. Even during the warranty term, the Company shall repair any defects arising from causes other than within the scopeof the warranty as specified above, at the owner's cost.

<Notes on Safety>●: WARNING○: CAUTION●System Safety- This system is intended for general industrial applications. It does not include functions for supporting applications requiring higher levels of safety such as safety-related devices or accident prevention systems. The
product must not be used for these purposes.
- Always turn off the power before attempting to mount or replace.
○System power supply
Use a stable, 24V DC power supply. Use of an unstable power supply may cause problems with the system.
○Separately route high-voltage and power cables
Although the AnyWireASLINK system has a high noise margin, keep the transmission line and I/O cables away from high-voltage and power cables.
○Connector and terminal connection* Pay careful attention to the length and installation of cable wiring to ensure that connectors and cables are neither overloaded nor disconnected.
* Make sure to prevent any metal objects from getting inside the connectors or the terminal blocks.
* Short-circuits caused by metal objects or mis-wiring are likely to damage the device.
○Do not impose any external loads on the units. Doing so may cause a failure.
○Do not disconnect or reconnect between the transmission line and slave units. A malfunction may occur.
○Use the AnyWireASLINK system within the range of the specifications and conditions shown below.

Comments/suggestions about AnyWire products:

ISO9001 / 1400
Certification

Anywire Corporation□ Headquarters
1 Babazusho, Nagaokakyo-shi, Kyoto 617-8550 JAPANhttp://www.anywire.jp
ISO9001 Applicable scope: Headquarters, East Japan Office, Kyoto Factory
ISO14001 Applicable scope: Headquarters, Kyoto Factory

2018 copyright Anywire Corporation in Japan, May 2018 alpcl-e