Hydrophobic HEPA V-Panel Filters Maintain Clean Turbines
Maintain High Power Output
GORE® Turbine Filters provide filtration through use of apatented multi-layer construction to capture ≥99.5% of allcontaminants and block water ingestion. This eliminates
power losses and maintains clean compressor efficiency.

Gas molecules
pass throughthe membrane.

Liquid andparticles
are repelled.

Eliminate Off-Line Washes
By capturing virtually all particulates, many users are able
to eliminate shutdowns for water washing. This increases
machine availability and reliability. Many turbines that use
Gore filters have been running for tens of thousands of hours
without the need to shut down for water washing.

Low Pressure Drop

Pressure Drop (inch of water)

1.25

V151.00

V18• High burst pressure

300• Proven lifetime250• Low initial pressure drop

200

0.75

150
0.50
100
0.25

0500
1000

1000

1500
2000

• Hydrophobic membrane prevents water ingress

350

Pressure Drop (Pa)V120

• E12 filtration efficiency ≥99.5 at MPPS
• Stops penetration of particles and dissolved salts

1.50

0.00

Key Features

2000
3000

2500
4000

3000

Key Benefits• Eliminates compressor fouling and associatedpower loss

50

• Reduces turbine wear0• Eliminates off-line water washings

3500

5000

CFM(m³/h)

Flow Rate

Stop Salt and Water Ingress• Maintains consistent low heat rate
• Reduces salt induced corrosion

1. Gore’s high efficiency (≥99.5%) multi-layer composite
removes salt crystals and other submicron particulates
from passing through the filter.
2. Gore’s hydrophobic membrane blocks both water anddissolved salts from entering the compressor. This
prevents corrosion damage which can contribute to
unexpected failures and major outages.

www.gore.com/turbinefilters

Hardware

HEPA Filter

Coarse Wrap

Filter Grid

Prefilter Holding Frame

Prefilter

Construction Materials

Dimensions

Filter Media

Fully synthetic composite
with ePTFE membrane

Filter Frame

High strength plastic

Potting

Polyurethane

V12
Part # TPV001 595 mm 553 mm 595 mm 550 mm 297 mm(23.4 in) (21.8 in) (23.4 in) (21.7 in) (11.7 in)Part # TPV004 595 mm 559 mm 595 mm 550 mm 297 mm(23.4 in) (22.0 in) (23.4 in) (21.7 in) (11.7 in)GasketPolyurethane (FIP)

V15Part # TPV002

Application Performance
Efficiency

Wet Burst Pressure

Part # TPV005

E12 according to EN 1822
Min. 99.5% @MPPS(Most Penetrating Particle Size)≥6250 Pa (25 in wg)

Part # TPV008

Initial Pressure DropV12235 Pa @ 3400 m3/h
(0.94 in wg @ 2000 cfm)

V15

180 Pa @ 3400 m3/h
(0.71 in wg @ 2000 cfm)

1000 Pa (4.0 in wg)

Temperature Range-40°C to +65°C (-40°F to +149°F)

Flame Retardant

Tested to UL900

W. L. Gore & Associates
Americas
W. L. Gore & Associates, Inc.
101 Lewisville Road
Elkton, MD 21921
USAPhone: +1 410 392 3300
Fax: +1 410 398 6624

EuropeW. L. Gore & Associates GmbH
Hermann-Oberth-Str. 26
D-85640 Putzbrunn
Germany
Phone: +49 89 4612-2211
Fax: +49 89 4612-2302

W2

D595 mm 553 mm 595 mm 550 mm 470 mm(23.4 in) (21.8 in) (23.4 in) (21.7 in) (18.5 in)
595 mm 559 mm 595 mm 550 mm 470 mm(23.4 in) (22.0 in) (23.4 in) (21.7 in) (18.5 in)D
W2

Suggested Final
Pressure Drop

GORE and designs are trademarks of W. L. Gore & Associates.
© 2012, 2014, 2016 W. L. Gore & Associates, Inc.
Covered by the following patents: EP16741441, US7501003, US8147583, US9205359

W1595 mm 553 mm 595 mm 550 mm 396 mm(23.4 in) (21.8 in) (23.4 in) (21.7 in) (15.6 in)
595 mm 559 mm 595 mm 550 mm 396 mm(23.4 in) (22.0 in) (23.4 in) (21.7 in) (15.6 in)

W1

155 Pa @ 3400 m3/h
(0.62 in wg @ 2000 cfm)

E-Mail: turbinefilters@wlgore.com

H2

Direct replacement of most conventional filters with nomodifications required to filter housing.

V18

www.gore.com/turbinefilters

V18
Part # TPV003

H1

H1

H2All data expressed as typical values. Please contact W. L. Gore & Associates directly toconfirm current information and to verify data for a specific part number. Specifications
are subject to change.

Contact a Gore application engineer for assistance in determining
the appropriate GORE® Turbine Filter for your specific application.
FOR INDUSTRIAL USE ONLY.
Not for use in food, drug, cosmetic or medical device manufacturing,processing, or packaging operations.
Middle East
W. L. Gore & Associates GmbH Middle East - Abu Dhabi
P. O. Box 11 44 70
Al Reem Island, Sky Tower, Office 609
Abu Dhabi
UAE
Tel: +971 2 5089444
Fax +971 2 5089445

GTF-024-R2-DSH-US-FEB17

Easy to Install Prefilter System(no tools required)