MODEL: M6SWVS
Tension-Clamp Ultra-Slim Signal Conditioners M6S Series

SIGNAL TRANSMITTER(two isolated outputs)
Functions & Features• Maintenance-free tension clamp connection• 5.9-mm wide ultra-slim design• Low profile allows the M6S module mounted in a 120-mm
deep panel• Galvanically isolates process instrumentation signals• High-density mounting• Power indicator LED

5.9 [.23]

5: 0 – 5 V DC (Input resistance 1 MΩ min.)6: 1 – 5 V DC (Input resistance 1 MΩ min.)
4W: -10 – +10 V DC (Input resistance 1 MΩ min.)
5W: -5 – +5 V DC (Input resistance 1 MΩ min.)0: Specify voltage (See INPUT SPECIFICATIONS)[2] OUTPUT 1Current
A: 4 – 20 mA DC (Load resistance 280 Ω max.)
D: 0 – 20 mA DC (Load resistance 280 Ω max.)
Voltage
5: 0 – 5 V DC (Load resistance 5000 Ω min.)6: 1 – 5 V DC (Load resistance 5000 Ω min.)[3] OUTPUT 2Same range availability as Output 1
Y: None94[3.70]

POWER INPUTDC Power
R: 24 V DC
(Operational voltage range 24 V ±10 %, ripple 10 %p-p max.)

102[4.02]mm [inch][4] OPTIONS (multiple selections)
MODEL: M6SWVS-[1][2][3]-R[4]ORDERING INFORMATION• Code number: M6SWVS-[1][2][3]-R[4]Specify a code from below for each of [1] through [4].
(e.g. M6SWVS-AAA-R/K/UL/Q)• Special input range (For codes Z & 0)
• Specify the specification for option code /Q(e.g. /C01)[1] INPUT
Current
A: 4 – 20 mA DC (Input resistance 50 Ω)
B: 2 – 10 mA DC (Input resistance 100 Ω)
C: 1 – 5 mA DC (Input resistance 200 Ω)
D: 0 – 20 mA DC (Input resistance 50 Ω)
E: 0 – 16 mA DC (Input resistance 50 Ω)
F: 0 – 10 mA DC (Input resistance 100 Ω)
G: 0 – 1 mA DC (Input resistance 1000 Ω)
H: 10 – 50 mA DC (Input resistance 20 Ω)
Z: Specify current (See INPUT SPECIFICATIONS)
Voltage
3: 0 – 1 V DC (Input resistance 1 MΩ min.)
4: 0 – 10 V DC (Input resistance 1 MΩ min.)Response Time (0 – 90 %)blank: Standard (≤ 0.5 sec.)/K: Fast Response (Approx. 3.5 msec.)
Standards & Approvals
blank: CE marking/UL: UL approval, CE marking
Other Options
blank: none
/Q: Option other than the above (specify the specification)

SPECIFICATIONS OF OPTION: Q
COATING (For the detail, refer to our web site.)/C01: Silicone coating/C02: Polyurethane coating

GENERAL SPECIFICATIONSConnection
Input and output: Tension clamp
Power input: Via the Installation Base (model: M6SBS)
or Tension clamp
Applicable wire size: 0.2 to 2.5 mm2, stripped length 8 mm
Housing material: Flame-resistant resin (black)
Isolation: Input to output 1 to output 2 to power
Zero adjustment: -2 to +2 % (front)
Span adjustment: 98 to 102 % (front)
Power indicator LED: Green LED turns on when the power is
M6SWVS SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-7977 Rev.9 Page 1/4

MODEL: M6SWVS
supplied.

INPUT SPECIFICATIONS■ DC Current: Input resistor incorporated
Specify input resistance value among followings for code Z.
20Ω, 50Ω, 100Ω, 200Ω, 249Ω, 1000Ω
(0.125 W ≥ [Input current]2 × R)
■ DC Voltage: -30 – +30 V DC
Minimum span: 100 mV
Offset: Max. 1.5 times span
Input resistance: 1 MΩ min. (10 kΩ min. with no powersupplied)

INSTALLATIONPower consumption: Approx. 0.6 W
Operating temperature: -20 to +55°C (-4 to +131°F)
Operating humidity: 30 to 90 %RH (non-condensing)
Mounting: Installation Base (model: M6SBS) or DIN rail
Weight: 60 g (2.1 oz)

PERFORMANCE in percentage of span
Accuracy: ±0.1 %Temp. coefficient: ±0.01 %/°C (±0.006 %/°F)
Line voltage effect: ±0.1 % over voltage range
Insulation resistance: ≥ 100 MΩ with 500 V DC
Dielectric strength: 2000 V AC @1 minute (input to output
1 to output 2 to power to ground)

STANDARDS & APPROVALS
EU conformity:
EMC Directive
EMI EN 61000-6-4
EMS EN 61000-6-2
RoHS DirectiveApproval:
UL/C-UL nonincendive Class I, Division 2,
Groups A, B, C, and D hazardous locations(ANSI/ISA-12.12.01, CAN/CSA-C22.2 No.213)
UL/C-UL general safety requirements(UL 61010-1, CAN/CSA-C22.2 No.61010-1)

M6SWVS SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-7977 Rev.9 Page 2/4

MODEL: M6SWVS
EXTERNAL VIEW
(With the cover open)
Power LED
Zero Adj.
Span Adj.

Zero Adj.
Span Adj.

Output 1

Output 2

EXTERNAL DIMENSIONS & TERMINAL ASSIGNMENTS unit: mm [inch]
SCREWDRIVER *INSERTION ANGLE: approx. 35°
WIRE INSERTION ANGLE: approx.35°

56

TEST PROBEmax. 2 [.08] dia.

78

DIN RAIL HOOK

94 [3.70]

DIN RAIL
35mm wide

15.9 [.23]234

SCREWDRIVER
INSERTION ANGLE: approx. 40°(0.5 [.02])

102 [4.02]• When mounting, no extra space is needed between units.
*Use a minus screwdriver: tip width 3.8 mm max., tip thickness 0.5 to 0.6 mm

M6SWVS SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-7977 Rev.9 Page 3/4

MODEL: M6SWVSSCHEMATIC CIRCUITRY & CONNECTION DIAGRAM
Isolation+ 3INPUT*Z

Low Drift
AmplifierS

OutputDriver– 45 +OUTPUT 16 –Z

S

OutputDriver

1 +OUTPUT 22 –POWER LED

7 +
POWER

CONNECTOR

8 –

POWER

* Input shunt resistor incorporated for current input.
Remark: The section enclosed by broken line is only with 2nd output option.

Specifications are subject to change without notice.

M6SWVS SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-7977 Rev.9 Page 4/4