PATLABOR™

INSTRUCTION MANUALDISCRETE INPUT TOWER LIGHT(super-small size, 60 mm dia., 1 - 5 layers)

BEFORE USE ....
Thank you for choosing us. Before use, please check contents of the package you received as outlined below.
If you have any problems or questions with the product,
please contact our sales office or representatives.
This product is for use in general industrial environments,
therefore may not be suitable for applications which require
higher level of safety (e.g. safety or accident prevention systems) or of reliability (e.g. vehicle control or combustion control systems).
For safety, installation and maintenance of this productmust be conducted by qualified personnel.
■ PACKAGE INCLUDES:Tower Light..........................................................................(1)■ MODEL NO.
Confirm Model No. marking on the product to be exactly
what you ordered.
■ INSTRUCTION MANUALThis manual describes necessary points of caution when
you use this product, including installation, connection andbasic maintenance procedures.

POINTS OF CAUTION■ CONFORMITY WITH EU DIRECTIVES• Altitude up to 2000 meters.
• The actual installation environments such as panel configurations, connected devices, connected wires, may affect the protection level of this unit when it is integrated
in a panel system. The user may have to review the CE
requirements in regard to the whole system and employ
additional protective measures to ensure the CE conformity.
• The equipment is intended to be installed in a industrial
environment defined by EN 60947-5-1.
■ POWER INPUT RATING & OPERATIONAL RANGE• Locate the power input rating marked on the product andconfirm its operational range as indicated below:		 24 V AC rating: 24 V ±10%, 47 – 66 Hz, ≤ 4.8 VA		 24 V DC rating: 24 V ±10%, ≤ 4.2 W• Supplying any level of power other than specified above
can damage the unit or the power source.
• Power up characteristics of a power supply for the unit
must be such a way that the output voltage goes up within operational voltage range of the unit in 5 seconds.
• The power cables and the signal I/O cables for the unit
must be located separately.
• The power cables, the signal I/O cables and the communication cables should not be bundled together or placednear each other.
• To increase noise resistance of the power input wires,
twist the strands before connecting.

MODELIT60SA2■ GENERAL PRECAUTIONS• Before you remove the unit or mount it, turn off the power
supply and input signal for safety.
• The unit must not be subjected to external force.
• Do not rub the unit with organic solvent like paint thinner.
• Do not block the unit’s ventilation openings or use it inareas where heat accumulates.	Additionally, do not store or use it under high-temperature conditions.
• Do not use the unit in an environment where flammablegases are present. This may result in an explosion.
• Do not disassemble or modify the unit in any way. Doingso may result in a fire or an electrical shock.
• Do not store or use the unit in locations subject to direct
sunlight, or where excessive dust or dirt is present.
• The unit is a precision equipment. Do not store or use it
where large shocks or excessive vibration can occur.
• Observe the environmental conditions when using theunit.
• Wait at least 30 seconds before turning on the power supply after it was turned off.
■ ENVIRONMENT• Indoor use.
• Do not install the unit where it is subjected to continuousvibration. Do not subject the unit to physical impact.
• Environmental temperature must be within -10 to +55°C(14 to 131°F) with relative humidity within 30 to 90% RH
in order to ensure adequate life span and operation.
• Mount the unit on a flat and robust plate.
• Bolts torque: 0.3 – 0.4 N·m• Lamps are omnidirectional.
• The buzzer sound is directional in front of the unit.
■ INGRESS PROTECTION (IP65)• The IP code is conformable when the unit is mounted vertically, and the control panel cover is locked. The compartment, where connectors are located, is not protected.
• When opening the control panel cover, avoid humidityand dust penetration. Dry and clean it if condensation isformed, and close the cover locking tightly.
• In order to protect ingress of water or dust into the bottom compartment, mount the unit correctly on the flat
plane, and be sure that the gasket does not roll back or
dust is not on the gasket.
■ WIRING• Do not install cables close to noise sources (relay drivecable, high frequency line, etc.).
• Do not bind these cables together with those in which
noises are present. Do not install them in the same duct.
■ AND ....
• The unit is designed to function as soon as power is supplied, however, a warm up for 10 minutes is required forsatisfying complete performance described in the datasheet.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2397 Rev.2

P. 1 / 4

IT60SA2COMPONENT IDENTIFICATION■ FRONT VIEW
Lamp 1
Lamp 2
Lamp 3
Lamp 4Lamp 5

Volume KnobBuzzer Aperture
GasketTERMINAL CONNECTIONSConnect the unit as in the diagram below.
■ EXTERNAL DIMENSIONS unit: mm

A±460±1.5 dia.

Max thick 6

Lamp Layers
12345A
140172204236268

40±1.5 dia.
3 Bolts and Nuts (M3 )*Approx.1500
Lead wires

30±1dia.

* Consult us for other bolt length.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2397 Rev.2

P. 2 / 4

IT60SA2■ MOUNTING REQUIREMENTS unit: mm

30120°

120°

53 Holes (4 dia.)dia.

Front (Buzzer)*Wirng Hole 12dia.
*Protect wires to prevent scratching them at the edge of thecompartment.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2397 Rev.2

P. 3 / 4IT60SA2■ CONNECTION DIAGRAM

INPUTLAMP 1 INPUTRed LAMP 1*1

LAMP 2 INPUT

Amber LAMP 2*1

LAMP 3 INPUTGreen LAMP 3*1

LAMP 4 INPUTBlue LAMP 4*1

LAMP 5 INPUTWhite LAMP 5*1

BUZZER INPUT 12HzPurple

BUZZER1BUZZER INPUT 210HzCyan

BUZZER2LAMP BLINK INPUTBrown

BLINKPOWEROrangePOWCOMMON

GrayCOM*1. Example of 5 layers in order: red, amber, green, blue and white.
Lamp and wire color are the same.
■ WIRING TO INPUT SIGNAL• Contact input e.g.

• NPN input e.g.

• PNP input e.g.

TOWER LIGHT

TOWER LIGHT

ONON

LAMP1

BLINK

ON

LAMP1

BLINK

0.5 A

TOWER LIGHT

LAMP1

BLINK

LAMP2

LAMP2

LAMP2

LAMP3

LAMP3

LAMP3

LAMP4

LAMP4

LAMP4

LAMP5

LAMP5

LAMP5

BUZZER1BUZZER1BUZZER1BUZZER2BUZZER2BUZZER2

BLINK

BLINK

BLINK

POW

POWPOWCOM

0.5 ACOM0.5 ACOM

Note 1: If “On” and “Blink” are set simultaneously for a single lamp, “Blink” is disabled.
Note 2: If “On” is set for Buzzer 1 and Buzzer 2 simultaneously, Buzzer 2 is disabled.
Note 3: NPN input and PNP input are available only for 24 V DC.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2397 Rev.2

P. 4 / 4