MODEL: IT60RETower Light Series[2] LAMP 2 COLORETHERNET TOWER LIGHT(60 mm dia., 4 layers)
Functions & Features• Lighting, blinking and buzzing available with PLC or PC via
Modbus/TCP.
• Bi-color lighting available in fourth layer• Separable tension clamp terminal(2nd layer from the top)
R: Red
Y: Amber
G: Green
B: Blue
W: White[3] LAMP 3 COLOR(3rd layer from the top)
R: Red
Y: Amber
G: Green
B: Blue
W: White98 (3.86)

667.4(26.27)mm (inch)[4] LAMP 4 COLOR(4th layer from the top)
R: Red
Y: Amber
G: Green
B: Blue
W: White98 (3.86)

MODEL: IT60RE-4[1][2][3][4][5]D[6]-[7][8]ORDERING INFORMATION• Code number: IT60RE-4[1][2][3][4][5]D[6]-[7][8]Specify a code from below for each of [1] through [8].
(e.g. IT60RE-4RYGBWD1-M2/Q)• Specify the specification for option code /Q(e.g. /C01)[5] LAMP 5 COLOR
R: Red
Y: Amber
G: Green
B: Blue
W: White
N: NoneMOUNTING
LAMP LAYERS

D: Direct mounting

4: 4 layers[6] DESIGN TYPE
[1] LAMP 1 COLOR(1st layer from the top)
R: Red
Y: Amber
G: Green
B: Blue
W: White

1: Type 1
2: Type 2 (with dummy antennae)(refer to outline dimensions)[7] POWER INPUTAC Power
M2: 100 – 240 V AC (Operational voltage range 85 – 264 V,
47 – 66 Hz)
DC Power
R: 24 V DC
(Operational voltage range 24 V ±10 %, ripple 10 %p-p max.)

IT60RE SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-2363 Rev.7 Page 1/5

MODEL: IT60RE[8] OPTIONSCOMMUNICATION

blank: none/Q: With options (specify the specification)

Communication Standard: IEEE 802.3u
Transmission: 10BASE-T, 100BASE-TX
Baud rate: 10/100 Mbps (Auto Negotiation function)
Protocol: Modbus/TCP
Data: RTU (Binary)Max. number of socket connections: 2Transmission media: 10BASE-T (STP, Category 5) 100BASETX (STP, Category 5e)Max. length of fieldbus segment: 100 meters
IP address: 192.168.0.1 (factory setting);
Selectable with PC Configurator Software
Port No.: 502
Ethernet indicator LED: Link, Link100, COL

SPECIFICATIONS OF OPTION: Q
COATING (For the detail, refer to our web site.)/C01: Silicone coating/C02: Polyurethane coating/C03: Rubber coating

RELATED PRODUCTS• PC configurator software (model: ITCFG)
Functions are configurable using the PC Configurator
Software.
Downloadable at our web site.
A dedicated cable is required to connect the module to thePC. Please refer to the internet software download site or
the users manual for the PC configurator for applicable
cable types.

GENERAL SPECIFICATIONS
Degree of protection: IP 65, vertical mounting only (bottomconnectors excluded)
Connection
Power: Separable tension clamp terminal
Applicable wire size: 0.2 to 1.5 mm2, stripped
length 10 mm
Network: RJ-45 Modular JackRecommended solderless terminal:
AI0,5-10WH 0.5mm2 (Phoenix Contact)
AI0,75-10GY 0.75mm2 (Phoenix Contact)
Housing material: Flame-resistant resin (white)
Lens: Flame-resistant resin (transparent)
Isolation: Network to power input to FE1 (Functional Earth)
DIP SW Setting: Frequency of lamp blinking and buzzing
discontinuance, buzzing volume level and output atconnection failed. (refer to the instruction manual)Lamp: Red, amber, green, blue and white LEDs
on/blinking (approx. 2 Hz, 10 Hz)
Indicator LEDs: Power, Run, Link, Link100, COL (5 LEDs)
indicate the module’s operating conditions. (Refer to theinsruction manual)Buzzing: Approx. 3.3 kHz
Interval: continuous/intermittent (approx. 2 Hz, 10 Hz)

INSTALLATIONPower consumption•AC: Approx. 6 VA at 100 V
Approx. 8 VA at 200 V
Approx. 9 VA at 240 V•DC: Approx. 3 W
Operating temperature: -10 to +55°C (14 to 131°F)
Operating humidity: 30 to 90 %RH (non-condensing)
Atmosphere: No corrosive gas
Mounting: Direct mounting
Mounting direction: Vertical
Weight: 1.4 kg (3.1 lb)

PERFORMANCE
Insulation resistance: ≥ 100 MΩ with 500 V DC
Dielectric strength: 1500 V AC @ 1 minute(network to power to FE1)

STANDARDS & APPROVALS
Refer to the manuals to comply with the standards.
EU conformity:
EMC Directive
EN 60947-5-1
Low Voltage Directive
EN 60947-5-1
24 V DC power
Installation Category III
Pollution Degree 3
100 – 240 V AC power
Installation Category II
Pollution Degree 2
Network to power: Reinforced insulation (300 V)
RoHS Directive
Protection against access to the terminal blocks:
Finger protection (VDE 0660-514)

IT60RE SPECIFICATIONS

MG CO., LTD.
www.mgco.jpES-2363 Rev.7 Page 2/5

MODEL: IT60RE
EXTERNAL VIEW
■ BOTTOM VIEW

■ FRONT VIEWFRONTPower Input Connector

Lamp 1Ethernet
Modular Jack

Lamp 2
Lamp 3ETHERNET
1 U (+)
2 V (–)
3 NC
4 NC
5 FE1

Lamp 4, Lamp 5PowerRun
Link
Link100
COL
WLAN 1WLAN 2

Buzzer Aperture
Status Indicator LEDREAR

Control Cover LockOn
12345678

Operating Mode
DIP SW
Configurator Jack

ConfigControl Panel Cover
Gasket

BOTTOMTERMINAL ASSIGNMENTS■ POWER CONNECTOR

12345

1. U (+)
2. V (–)
3. NC
4. NC
5. FE1POWER INPUT (+)
POWER INPUT (–)
UnusedUnusedFUNCTIONAL EARTH

IT60RE SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-2363 Rev.7 Page 3/5

MODEL: IT60RE
EXTERNAL DIMENSIONS unit: mm(98)*1(R*8)

14667.4 ±4528.9 ±41

60 ±1.5 dia.

13 ±1.5*2

80 ± 1.5 dia.

98 ±1.5 dia.

(150)

4 Bolt Nuts (M4).5 dia.

73 ±1(58*1. Only for DESIGN TYPE option code 2.
*2. Consult M-System for other bolt length.

dia.

)

MOUNTING REQUIREMENTS unit: mm73.

0 diaole 5gH
Wirindia.

4 Holes (5 dia.)

Front*Protect wires to prevent scratching them at the edge of thecompartment.

IT60RE SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-2363 Rev.7 Page 4/5

MODEL: IT60RE
SCHEMATIC CIRCUITRY & CONNECTION DIAGRAM

RJ-45JACK

To other Ethernet devices

Comm.
Circuit

LED 1 – 5

1

BuzzerV (–)

2

STATUS
INDICATOR LED

NC

3NC

4FE15U (+)
POWERCONFIGURATOR JACK

Control
CircuitDIP SW

Miniature JackSpecifications are subject to change without notice.

IT60RE SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-2363 Rev.7 Page 5/5