C series

MULTI-POINT TEMPERATURE CONTROL SYSTEMC SERIES

Setting the standard in multi-point temperature control

Save space by connecting only necessary points
C series is a multi-channel temperature control system which consists of power source host link unit,
2-ch temperature control unit, etc.
Approximately 50% less wiring is used than the usual type 1 channel temperature controllers.
SHINKO touch panel unit can be connected to other temperature control units without programmingand performs various settings (setting parameters for temperature control, temperature alarmfunction, heater burnout alarm function, etc).
By connecting to a host computer or the PLC, even multiple tasks of monitoring can be carried out.
Use of a CC-Link link unit allows you to connect to a higher speed Open Network.
Sequence control and process control can be united by connection to CC-Link compatible PLC,
other measuring instruments or controllers.

Save space and wiring !

Connectable to CC-Link compatible devices！

Temperature control unit (CCT-235), CC Link link unit (CLT-200): 24
x 96 x100mm (W x H x D)
Power source host link unit (CPT-20A), PLC interface unit (CIT-200):
48 x 96 x 100mm (W x H x D)
Space for up to 20 points of temperature control: 288 x 96 x 100mm(W x H x D)
By using a base unit, a big reduction of wiring for communication andpower supply has been achieved.

Connection to Open Network via a CC-Link link unit (CLT-200)
enables data processing by 10Mbps of maximum transmission
speed and wider variety of applications.
Up to 8 units of temperature control unit (CCT-235) per blockand 1 unit of CC-Link link unit (CLT-200) make 16 points of temperature control possible.
Multi-drop connection of the blocks enables maximum 256
points (16 blocks) of temprature control .

Easy-to-use SHINKO touch panel unit！

Simple connection and removal！

You can operate the C series interactively with just a touch of a finger.
(Software for screen editing is available, so you can create your own
display.)
Console unit for simplified monitoring (COT-200: 96mm square type)is also provided at a low cost.

Each unit can be easily connected and removed with one touch.
■ How to connect and remove

Multi-point (max. 320 points) temperature control！
With host link unit system, up to 10 units of temperature control unit
(CCT-235) per block can be connected, which means that a [288 x
96 x 100mm (W x H x D)] unit can control 20 points of temperature
control.
With multi-drop connection for power source host link unit (CPT-20A),
maximum 16 blocks (320 points) of multi-point temperature control
system can be achieved.

Hook the unit into the upper
part of the base and insert it
into the base.
Lock mechanism ensures thatthe unit is fixed tightly to thebase enough to be resistantagainst vibration, and this also
ensures easy maintenance.

System configuration example[ Wiring connection when controlling with 1 block of C series ]Communication
cable (sold separately)(Model : CPM)
When performing 20 points or less of temperature control, it is possible to connect the SHINKO touch panel unit (CMT-200)
to the temperature control units without programming.
One block consists of the CPT-20A (1 unit) and CCT-235 (1 to 10 units).
(Software for screen editing is available, so you can create your own display.)[ Wiring connection when connecting Console unit to 1 block of C series ]The Console unit in this application is used to provide 20 points or less of control at a low cost.
External dimensions of Console unit (COT-200): 96×96×110mm（W×H×D）
One block consists of the CPT-20A (1 unit) and CCT-235 (1 to 10 units).

[ Wiring connection when controlling with plural blocks of C series ]Communication
converter
IF-300-C5,etc.

Personal computer

When performing 20 points or greater of temperature control, use a communication converter (IF-300-C5, etc.).
With multi-drop connection by RS-422A between the CPT-20A and communication converter, maximum 16 blocks (320 points) oftemperature control can be performed.
One block consists of the CPT-20A (1 unit) and CCT-235 (1 to 10 units).
Using C series monitoring software compatible with Microsoft Windows, various parameters setting,PV monitoring, SV changing, data logging and data trending can be carried out.

[ Wiring connection when connecting the PLC to 1 block of C series ]

CPU
unit

PLC
Link unit
By connecting to the PLC, 20 points or less of temperature control can be performed.
One block consists of the CPT-20A (1 unit) and CCT-235 (1 to 10 units).

PLCs SHINKO C series can be applied:
MELSEC-A series, FX2N series, Q series : Mitsubishi Electric Corporation
SYSMAC C200H : Omron Corporation
MICREX-F70 : Fuji Electric Co., Ltd.
and others
For products not described here, please contact us.

[ Wiring connection when connecting the PLC to plural blocks of C series ]

CPU
unit

PLC
Link unit

When performing 20 points or greater of temperature control while connected to the PLC, maximum 16 blocks (320 points) oftemperature control can be performed via the PLC･Interface unit (CIT-200) with multi-drop connection.
One block consists of the CPT-20A (1 unit) and CCT-235 (1 to 10 units).

[ Wiring connection when connecting the CC-Link compatible PLC to 1 block of C series ]

CPU
unit

PLC
CC-Link master unit
By connecting the CC-Link compatible PLC, 16 points or less of temperature control can be performed.
At this time, one CC-Link link unit (CLT-200) should be used in one block, and connected with the CC-Link compatible cablebetween CC-Link master unit of the PLC and CC-Link link unit (CLT-200).
With multi-drop connection of CC-Link link unit (CLT-200), maximum 16 blocks (256 points) of temperature control can be
performed.
One block consists of the CPT-20A (1 unit), CCT-235 (1 to 8 units) and CLT-200 (1 unit).

2-channel temperature control unit CCT-235
There are 2 types of input and 3 types of control output (common to input 1 and input 2).
Control action (PID, PD, ON/OFF) can be selected by the command.
When ordering, specify as follows.
CCT-235-2□／□, □Option ……………W: Heater burnout alarm, TC: Terminal cover
Input………………E : Thermocouple (K, J, R, B, PL-Ⅱ, N), R: RTD (Pt100, JPt100), V: Voltage, C: Current
Control output……R : Relay contact, S: Non-contact voltage, A: DC current
Mounting method
Base unit mounting
Setting accuracy
Within±0.3%FS±1digit
K: -200 to 1370℃(-320 to 2500 ) or 0.0 to 600.0℃(0.0 to 999.9 ), J: -200 to 1000℃(-320 to 1800 ) or 0.0 to 600.0℃(0.0 to 999.9
Input and rated scale R: 0 to 1760℃ (0 to 3200 ), B: 0 to 1820℃ (0 to 3300 ), PL-Ⅱ: 0 to 1390℃ (0 to 2500 ), N: 0 to 1300℃ (0 to 2300 )Pt100: -199.9 to 850.0℃ (-199.9 to 999.9 ), JPt100: -199.9 to 500.0℃ (-199.9 to 900.0 )Alarm 1 or Alarm 2 can be selected by the command from the following 13 types.
Alarm function is set by ± deviation to the main setting (except the alarm actions marked *).
AlarmHigh limit alarm, Low limit alarm, H/L limits alarm, H/L limit range alarm, Process high alarm*, Process low alarm*,
High limit alarm w/standby, Low limit alarm w/standby, H/L limits alarm w/standby, H/L limit range alarm w/standby
Process high alarm w/standby*, Process low alarm w/standby*and No alarm.
Setting accuracy --- Within±0.3%FS±1digit
Action ----------------- ON/OFF action
Hysteresis ----------- TC: 0.1 to 100.0°
C(°F), DC voltage, DC current: 1 to 1000
Power supply
5±0.2V DC max.100mA, 12 +2０V DC max.50mA (The power is supplied by the CPT-20A.)
Power consumption
Approx. 3VA
Rating (Shipped as specified type.) (Option)
Heater burnout
Case, Color
Flame-resisting resin, Black･20A: When option [W(20A)] is applied.
alarm [W]
External dimensions
24×96×100mm (Ｗ×Ｈ×Ｄ)･50A: When option [W(50A)] is applied.
WeightApprox. 110g
Terminal cover [TC]Electrical shock protection terminal cover (Option))

Power source host link unit CPT-20A
Link unit to supply the power to the CCT-235 and for communication with touch panel unit, a host computer, etc.
Mounting method
Base unit mounting
Communication line
: Based on RS-422A(RS-485)
Contact input
Communication method: Half-duplex communication
Terminal ⑤ and ⑧ Closed: DI1 ON, Open: DI1 OFF
Digital input
start-stop synchronous
Terminal ⑥ and ⑧ Closed: DI2 ON, Open: DI2 OFF
Communication speed : 9600, 19200bps
Terminal ⑦ and ⑧ Closed: DI3 ON, Open: DI3 OFF
Host communication(Selectable by DIP switch.)function
Relay contact: 1a×3 (various alarm outputs)
Data format Start bit : 1
Data bit : 7
Digital output
Contact capacity: 250V AC 3A (resistive load)Parity : Even parity
250V AC 1A (inductive load cosφ=0.4)
Stop bit : 1
Supply voltage
100 to 240V AC 50/60HzPower supply output for CCT and CLT 5±0.2V DC 2.0A， 12 +2０ V DC 0.8A
Allowable voltage
Power consumption
Approx. 28VA (When connecting 8 units of the CCT
85 to 264V AC
fluctuationand one unit of CLT-200)
WeightApprox. 290g
Case, Color
Flame-resisting resin, Black
External dimensions
48×96×100mm（Ｗ×Ｈ×Ｄ）
Terminal cover [TC]Electrical shock protection terminal cover (Option)

PLC interface unit CIT-200
With multi-drop connection, up to 16 blocks can be connected.
Mounting method
DIN rail mounting
Communication line :Based on RS-232C and RS-422A(RS-485)
Built-in terminator (120Ω) between RXA and RXB
of RS-422A.
Communication method : Half-duplex communication
PLC communication
start-stop synchronous
function
Communication speed : 9600, 19200bps(Selectable by DIP switch)
Data format Start bit : 1
Data bit : 7, 8
Parity : No, Even and Odd
Stop bit : 1, 2
Supply voltage
100 to 240V AC 50/60Hz
Allowable voltage fluctuation 85 to 264V AC
Power consumption
Approx. 5VA

Communication
function between
the CIT and CPT

Communication line : Based on RS-422A (RS-485)
Built-in terminator (120Ω) between RXA and RXB
of RS-422A.
Communication speed: 19200bps
Data format Start bit : 1
Data bit : 7
Parity: Even parity
Stop bit : 1

Case, Color
External dimensions
WeightTerminal cover [TC]

Flame-resisting resin, Black
48×96×100mm (Ｗ×Ｈ×Ｄ)
Approx. 300g
Electrical shock protection terminal cover (Option)

CC-Link link unit CLT-200
Link unit to connect CC-Link master unit
The number of occupied station for CC-Link is 4.
Mounting method
Base unit mounting
Setting
Baud rate and address of the CC-Link can be set by the rotary switch.
Communication line : CC-Link (RS-485)
Host communication
Communication method : CC-Link method
function
Communication speed : 156k，625k，2.5M，5M，10Mbps (Selectable by the Rotary switch.)
Supply voltage
5±0.2V DC max. 200mA (Supplied by the CPT-20A.) External dimensions
24×96×100mm（Ｗ×Ｈ×Ｄ）
Power consumption
Approx. 2VA
WeightApprox. 100g
Case, Color
Flame-resisting resin, Black
Terminal cover [TC]Electrical shock protection terminal cover (Option)

PC link unit CLT-20S
Mounting method

Base unit mounting
Communication line : RS-232C or RS-422A/RS-485
Communication method : Half-duplex communication start-stop synchronous
Communication speed : 2400bps, 4800bps, 9600bps, 19200bps (Selectable by the Rotary switch) (Default: 9600bps)
Host communication Data format Start bit : 1
function
Data bit : 7
Parity : Even parity
Stop bit : 1
Supply voltage
5±0.2V DC
External dimensions 24 x 96 x 100mm (W x H x D)
Power consumption Approx. 1VA
WeightApprox. 90g
Case, Color
Flame-resisting resin, Black
Terminal cover [TC] Electrical shock protection terminal cover (Option)

SHINKO touch panel unit CMT-200
Touch panel unit to set the CCT-235 individually
Monitoring of 20 points per block can be carried out.
Connection to the controller without programming is available.

Displayspecifications

Input
specifications
External interface
Mounting method
External dimensions
WeightDevice: Color LCD
Color: 16 out of 512 colors
Number of dots
: 320×240 dots
Size
: 5.7 inches
Effective area
: 115.2×86.4mm (H×V)
Number of characters : Half size (8×16 dots) 40 characters×15 lines, Full size (16×16 dots) 20 characters×15 lines
Switch system: Transparent conductive touch switch
Number of touch switch : 16×12
Serial: RS-232C 1 port, RS-485 1 port (Multi-drop possible)
Dust-proof･Drip-proof IP65F (When using drip-proof packing for front panel)
Flush
Supply voltage
24V DC
195×150×47mm（W×H×D）
Allowable voltage fluctuation 20.5 to 28.8V DC (24W or less)
850g or less

Console unit COT-200
The setting and monitoring per channel can be performed.
When using COT-200, only 20 points of temperature setting per block can be performed.
Mounting method

Flush
Communication line : Based on RS-422A
When communication error occurs, the output isCommunication method : Half-duplex communication
turned on.
Communication
start-stop synchronous
Relay contact: 1aerror output
Communication speed : 19200bps
Control capacity : 250V AC 3A (resistive load)
Serial communication
Data format Start bit : 1
250V AC 1A (inductive load cosφ=0.4)
Data bit : 7
Supply voltage
100 to 240V AC 50/60Hz
Parity : Even parity
Allowable voltage fluctuation 85 to 264V AC
Stop bit : 1
Power consumption
Approx. 5VA
External dimensions
96×96×110mm（Ｗ×Ｈ×Ｄ）
Case, Color
Flame-resisting resin, Light gray
WeightApprox. 500g
Terminal cover [TC]Electrical shock protection terminal cover (Option)
When the status signal of temperature alarm, heater burnout alarm, loop break alarm, Overscale and Underscale
Status output [SO]in any channel of CCT-235 connected is turned on, the output of COT-200 will be also turned on.
(Option)Open collector: Capacity 24V DC, max. 50mA

Base unit CBT-200
Base unit for mounting the CPT, CCT and CLT
Mounting method
DIN rail mounting
CBT-205 : When connecting a host computer , CMT-200 or COT-200, 1 unit of CPT and max. 5 units of CCT can be connected.
When connecting CC-Link compatible PLC, 1 unit of CPT, max. 4 units of CCT and 1 unit of CLT can be connected.
Model name
CBT-210 : When connecting a host computer , CMT-200 or COT-200, 1 unit of CPT and max. 10 units of CCT can be connected.
When connecting CC-Link compatible PLC, 1 unit of CPT, max. 8 units of CCT and 1 unit of CLT can be connected.
CBT-205 : 168×96mm（Ｗ×Ｈ）
Base, Color
Flame resisting resin, Black
External dimensions
CBT-210 : 288×96mm（Ｗ×Ｈ）
WeightCBT-205: Approx. 200g CBT-210: Approx. 300g

Communication cable CPM, CPP
Communication cables for connecting between CPT and CMT, between CPT and COT, or for increasing the blocks

Model name

CPM: Communication cable to connect between CPT-20A and CMT-200, or between CPT-20A and COT-200.
Cable length: 3m.
CPP : Communication cable to connect between CPT units (to increase the blocks).
Cable length: 50cm.
For inquiries about extending the CPM, CPP or other communication cables, please contact us or our agency.

External dimensions
ＣＣＴ−２３５

ＣＰＴ−２０Ａ

ＣＬＴ−２００

ＣＯＴ−２００ＣＩ
Ｔ−２００

ＣＢＴ−２００
ＣＭＴ−２００For96

ＣＬＴ−２０Ｓ

24

94

Terminal arrangement
ＣＣＴ−２３５

ＣＰＴ−２０Ａ

ＣＩ
Ｔ−２００

TX
RX

RS-232C

COM
TXA
T XB
RXA
RXB
AC 100〜240V
50／60HzGroundCOM

RS- 422A

Terminal arrangement

ＣＯＴ−２00

ＣＬＴ−２00

・A1 ：Alarm 1
・A2 ：Alarm 2
・HB：Heater burnout alarm
・L A ：Loop break alarm

ＣLＴ−２0S

ＣＭＴ−２00

connector
RS-232C
FG

RS-422A／RS-485
FG
FG

TX

TXA

RX

TXB

・ YA
・YB

RXA

DC
(Power terminal)

RXB
COM

COM

COM

terminal

GroundWhat is CC-Link ?
Full name: Control and Communication Link
CC-Link is a field network system that processes both control and information data at high speed, to provide efficient, integrated factory and process automation.
By distributing CC-Link compatible instruments to the production line or machine devices, the wiring reduction of the entire system can be accomplished.
Connections can be made to different types of CC-Link compatible products, and functional combination of the products gives flexibility to the system
to fulfill your system requirements.

･ This catalog is as of December 2003, and specifications are subject to change without notice.
･ If you have any inquiries, please consult us or our agency.

SHINKO TECHNOS CO., LTD.
OVERSEAS DIVISION
Reg. Office: 2-48, 1-Chome, Ina, Minoo, osaka, 562-0015, Japan

Mail Address: P. O. Box 17, Minoo, Osaka, JapanTel: 81-72-721-2781

Fax: 81-72-724-1760

URL: http://www.shinko-technos.co.jp

E-mail: overseas@shinko-technos.co.jp
X3

204

C（E）