FSC-219-227

INSTRUCTION MANUAL(DETAILED VERSION)SWITCH CONTROL UNIT
FSC-110

FSC-219-227

Contents

Safety precautions ................................................................ 2
Composition of type ............................................................... 2

1 Product outline ...............................................................

3

2 Name and function of each part ................................................

3

3 Included items ................................................................

4

4 Dimension diagram .............................................................

4

5 Installation instructions .....................................................

4

6 Connection ....................................................................

5

7 Operation .....................................................................

5

8 Control / Monitoring mode .....................................................

6

8.1 Display (LED) .............................................................

6

8.2 ON/OFF control ............................................................

7

8.3 Annunciator sequence ...................................................... 10
9 Setting mode .................................................................. 12
9.1 Setting flow .............................................................. 12
9.2 Setting method ............................................................ 12
9.3 Setting menu .............................................................. 13
10 Test mode .................................................................... 15
10.1 Test flow ...............................................................

15

10.2 Test method .............................................................. 15
11 Specification ................................................................ 16
11.1 Rating ................................................................... 16
11.2 Detailed specifications .................................................. 16
12 Trouble shooting ............................................................. 181

FSC-219-227
Thank you for purchasing DAIICHI ELECTRONICS product.
Please read this instruction manual carefully before using.

Safety precautions
 Environment conditions
Please be sure to use this product in a place that meets the following conditions.
In places that do not meet this condition, it may cause malfunction or failure and product life decline.
 Within the range of ambient temperature -10 to +55 ℃, humidity 5 to 90％ RH.
 Place free of dust, corrosive gas, salt and oily smoke. (Corrosive gas：SO2 / H2S, etc.)
 Location that is not affected by vibration and shock.
 Location that is not affected by external noise.
 Altitude 2000m or less.
 Outdoor use conditions
 These products are not a dustproof, waterproof, and splash proof construction. Please avoid the placewith much dust. Moreover, please install in the place not exposed to rain or water drop.
 Please do not install in the place where sunlight hits directly. Discoloration and degradation of aname plate, and deformation of the case by the surface temperature rise may occur.
 Mounting and wiring
Please refer to this instruction manual for mounting and the wiring.
 Please refer to connection diagram for the wiring.
 Please avoid hot line work.
 Please use an electrical wire size suitable with the rated current.
 Please check the tightening of the screw.
 Preparation
This product must be set before use.

Please set correctly after reading this instruction manual.

 Maintenance and inspection
 Inspection in energized state is dangerous.
 No replacement in periodic inspection.
 After wiring change and maintenance, attach the terminal cover.
 Please wipe off lightly with the dry soft cloth. Please do not use the organic solvent, chemicals, cleaners,
etc., such as an alcohol, for cleaning.
 Storage
Please store in a place that meets the following conditions.
 The ambient temperature within -25 to +70 ℃ (storage temperature).
 Daily average temperature 40 ℃ or less.
 Location corresponding to the usage environment and use conditions.
 Aluminum electrolytic capacitors are used in products. Please energize the power supply within one
year after purchase.
 Countermeasures against troubles
If trouble occurs within the warranty period, DAIICHI ELECTRONICS will repairs this product.
 Disposal
Please dispose this product as industrial waste (non-combustible).
Mercury parts and a nickel-cadmium battery are not used for this product.
 Product replacement cycle
The recommended replacement period for this product is 10 years.
 Warranty period
The warranty period of the product is one year after the date of delivery.

Composition of typeType

Specification code

FSC - 110 -① Power supply② Communication output

1

100/110V AC

1

2

100/110V DC

CC-Link

2

FSC-219-227

1 Product outline
 The ON / OFF control of the switchgear can be performed local (front switch) or remote (CC-Link communication).
 Displays ON / OFF control of switchgear, control status (Local / Remote) and fault / operation due to
BI1 to BI4.
 The interlock function enables ON / OFF control during operation lock input and ON control lock during a warnig.
 BI ON / OFF (LED, communication output) can be checked without adding input.
 The guidance display by OLED makes setting easy.

2 Name and function of each partName label(31mm×11mm Max.)
ON/OFF control
display

Fault/Operation
display

REMOTE LED

LOCAL LED
OFF LED

ON LED

BI1 LED

BI3 LED

BI2 LED

BI4 LED

ON/OFF control
display

Fault/Operation
display

OLED

Switch ×7

Name

Function
LOCAL，
REMOTE

LED

Name label
OLED
ON
OFF
PERMISSIONLAMP RESET＋ALARM STOP－LAMP TESTMODE

LOCAL／REMOTE[SET]

Displays the control status of the switchgear (Local / Remote).
LED color：Amber
The status of the switchgear is lit by the answer signal.
ON，OFF
LED color ON：Red, OFF：Green
When fault / operation input (BI1 to BI4) is applied, it flashes or lights.
BI1 to BI4 Warning：Red, Caution：Amber, Operation：White / Green /Blue / Red (Inputs can be set individually)
Paste the name label of the fault or operation corresponding to each input. (Name label
need to be prepared by the user.)
Provides guidance on configuration and testing.
Used for "ON" control of switchgear. When pressed for 0.2 seconds or longer, “ON LED”
flashes and waits for ON control permission.
Used for "OFF" control of switchgear. When pressed for 0.2 seconds or longer,“OFF LED” flashes and waits for OFF control permission.
Used for "ON" or "OFF" control of switchgear. Pressing for 0.2 seconds or more in eachcontrol permission wait state operations the corresponding control output.
Control / Monitoring mode Resets fault indication (LED).
Using for change setting values and selecting items /Setting mode / Test modeelements.
Control / Monitoring mode Change the failure indicator LED from blinking to lit.
Setting mode / Test mode Used for change setting values and selecting items / elements.
Used to check the lighting of the LED.
Control / Monitoring mode Press the [SET] and MODE switches simultaneously for 3
seconds or longer to enter test mode.
Used to return to the control / monitoring mode or return toSetting mode / Test modethe previous screen.
Used for LOCAL / REMOTE switching with ON / OFF control.
Press [SET] for more than 3 seconds to switch to setting mode.
Control / Monitoring mode
Press the [SET] and MODE switches simultaneously for 3
seconds or longer to enter test mode.
Setting mode / Test mode Used for definite the setting values.

Description
page

3

P6 to P15－
P6 to P15
P7 to P9
P7 to P9
P7 to P9P10 to P14
P10 to P14

P10 to P14

P10 to P14

FSC-219-227

3 Included items① Instruction Manual (Installation and Operation) ･････ 1 pc
② M5 flange nut (for mounting) ････････････････････････ 2 pcs

4 Dimension diagram

φ99
2-M5 screw

90±0.5

φ

1±
10

1

Panel cut（Front view)

5 Installation instructions(1) Unit is put in a cut hole of a panel from the front.
Its body is inserted until it exceeds retaining
stopper of the lower base.
(2) Please fix the unit in place with attached
M5 flange nut with tightening torque of
2.0 to 2.5N･m.

490±0.5

M4 screwM4 screwM3 screw

103.5

(4.3)

16.5

110

110

2-φ7

FSC-219-227

6 Connection
Remove the terminal cover and connect correctly according to the connection diagram.
After wiring, attach the terminal cover.
＋ －
～ ～

ON

ANSWER (＋)

OFF ANSWER (＋)
BI1 (＋)
BI2 (＋)
BI3 (＋)
BI4 (＋)Input

ALARM STOP (＋)
LAMP RESET (＋)
OPERATION LOCK(＋)
BI COM(－)

Power supply
＋ －
～ ～

8
9
10
11
12
13
14
15

1
2

5
6
7

17
19
21
25
27
29

DA
DB
DG
Ter. 1
SLD
2
FG

16
18
20
24

ON

26

OFF

1

Communication output
CC-Link

Control output

28

Note(１) By shorting number 17 (DB) and number 19 (Ter.), termination resistor of 110Ω is internally connected.
Please use it only for the equipment which becomes terminated in connection form.
Note(２) FG is equivalent to functional ground, so dedicated ground or common ground is recommended.
SLD and FG are connected internally.

7 Operation
This product can switch to each mode (Control/Monitoring mode, Setting mode, Test mode) by switch operation.
You can also operate while checking the OLED display.
For the operation method in each mode, please refer to section 8 to 10.
POWER ON

Monitoring mode
Screen OFF

Setting mode

Start-up

Setting item selection
SET

SET
Press 3 seconds[ OLED ]Test mode
Test element selection

SET

MODE

SET and MODE
Press 3 seconds

MODE

(３)

10 minutes without
operation

Screen OFF

Note(３) From any screen, press MODE for 3 seconds or more to return to monitoring mode.
5

FSC-219-227

8 Control / Monitoring mode
8.1 Display (LED)Each LED (LOCAL, REMOTE, OFF, ON) is displayed according to the LOCAL control or REMOTE control timing chartin section 8.2 ON / OFF control. The lighting color of the LED is as follows.
Operation mode setting

Display

LOCAL，REMOTE

LED lighting color

OFF

Amber

Green

ON
Red

BI1 to BI4 LEDs display according in section 8.3 Annunciator sequence.
The lighting color of the LED is as follows.
Operation mode setting

Display

Warning

Operation (４)Caution

Red

Amber

White
Green

LED lighting color
Blue
Red
Note(４) The lighting color of the LED can be set individually for each input.

LOCAL LED

REMOTE LED

OFF LED

ON LED

BI1 LED

BI3 LED

BI2 LED

BI4 LED

6

FSC-219-227

8.2 ON/OFF control(1) LOCAL control
Coltrol (５)Control method① When ON is pressed for 0.2 seconds or longer, the “ON LED” flashes and waits for ON control
permission. (６) (While the “ON LED” is flashing, if you press ON again or do not
operate for 10 seconds, the waiting for ON control permission is canceled.)② ON control (control output) operates when PERMISSION is pressed for 0.2 seconds or more while
waiting for ON control permission. (10)③ When the ON answer input is applied and the “ON LED” lights up, the “ON” control is completed.
②

①
LOCAL

REMOTELOCAL

REMOTE

OPEN

CLOSE

OPEN

CLOSE

ON control

ON LED
flashes
ON control
operation.
Valid after 0.5
seconds after
ON operation

Press ON(６)(７)③LOCAL

REMOTE

OPEN

CLOSE

ON LED
flashes

LOCAL

REMOTE

OPEN

CLOSE

LOCAL

REMOTE

OPEN

CLOSE

ON LED
lightsON control
complete

Press PERMISSION(６)(７)LOCALREMOTE

OPEN

CLOSE

ON LED
flashes

ON LED
off(Cancel)Cancel operation.
Valid after 1 second
after ON operation
Press ON (６)(７)① When OFF is pressed for 0.2 seconds or longer, the “OFF LED” flashes and waits for OFF
control permission. (６) (While the “ON LED” is flashing, if you press OFF again or do not
operate for 10 seconds, the waiting for OFF control permission is canceled.)② OFF control (control output) operates when PERMISSION is pressed for 0.2 seconds or more while
waiting for OFF control permission. (10)③ When the OFF answer input is applied and the“OFF LED” lights up, the“OFF” control is completed.
①

②
LOCAL

REMOTE

OPEN

CLOSE

OFF LED
flashes

LOCAL

REMOTE

OPEN

CLOSE

ON LED
flashes

LOCAL

REMOTE

OPEN

CLOSE

OFF LEDlightsON control
complete③
LOCAL

REMOTE

OPEN

CLOSE

LOCAL

REMOTE

OPEN

CLOSE

OFF control
Press OFF
(８)(９)

OFF control
operation.
Valid after 0.5
seconds after
OFF operation
OFF LED
flashes
Cancel operation.
Valid after 1 second
after OFF operation

Press PERMISSION(８)(９)LOCALREMOTE

OPEN

CLOSE

OFF LED
off(Cancel)Press OFF (８)(９)Note (５) Operation is valid even in setting mode and test mode.
Note (６) When the ON LED is lights, the OFF LED is flaching, the warning has occurred, or the operation lock,the ON control operation is invalid.
Note (７) If ON and PERMISSION are pressed at the same time, the operation is invalid.
Note (８) When the OFF LED is lights, the ON LED is flaching, the operation lock, the OFF control operation is invalid.
Note (９) If OFF and PERMISSION are pressed at the same time, the operation is invalid.
Note (10) ON ontrol (control output) or OFF control (control output) is output for 1 second after control operation.

7

FSC-219-227■ LOCAL control timing chart
Invalid during operation lock
CancelInvalid

CancelInvalid during
warning

Invalid10s

ON (Switch)
Invalid
OFF (Switch)

Invalid

Invalid

PERMISSION(Switch)Operation lock (BI)LOCAL display LED
Flicker during
operation lock

REMOTE display LED

Flicker orlighting

Warning display

Flicker orlighting

Caution display
ON (control output)
(11)
1s

1s

OFF (control output)
(11)
1s

1s

ON Answer (BI)OFF Answer (BI)
FlickerFlickerFlickerFlicker

ON Answer (LED)
FlickerFlicker
OFF Answer (LED)ON Answer(Communication)
OFF Answer(Communication)

Note (11) Operating condition of control output
Equipment status
Control output
Operation lock
Warning indicate
ON control
OFF control
OFF
Allow
Allow
None
Flicker / Lighting
Disallow
Allow
OFF
Disallow
Disallow
Lock
Flicker / Lighting
Disallow
Disallow8

FSC-219-227(2) REMOTE control (CC-Link communication)
Operates according to the REMOTE timing chart.
Control

Control method

ON control

When an ON command (0E37H) is sent via CC-Link communication, ON (control output) is activated. (12)(For details, refer to the FSC-110 communication specification CC-Link protocol.)OFF control

When an OFF command (0EC8H) is sent via CC-Link communication, OFF (control output) is activated. (13)(For details, refer to the FSC-110 communication specification CC-Link protocol.)Note (12) Operation is invalid during in warning or while the operation is locked.
Note (13) Operations are disabled while the operation is locked.。

■ REMOTE control timing chart
Invalid during operation lock

Invalid during warning
ON command (CC-Link)

OFF command (CC-Link)

Operation lock (BI)LOCAL display LED

REMOTE display LED

Not flicker even during operation lock

Warning display

Flicker orlighting

Caution display

Flicker orlighting

ON (control output)(14)
OFF (control output)
(14)

1s

1s
ON Answer (BI)OFF Answer (BI)ON Answer (LED)OFF Answer (LED)ON Answer(Communication)
OFF Answer(Communication)

Note (14) Operating condition of control output
Equipment status
Control output
Operation lock
Warning indicate
ON control
OFF control
OFF
Allow
Allow
None
Flicker / Lighting
Disallow
Allow
OFF
Disallow
Disallow
Lock
Flicker / Lighting
Disallow
Disallow9

FSC-219-227

8.3 Annunciator sequence
Operates according to the annunciator sequence.
Operation mode setting

Operation (15)
LAMP
TEST

Warning
CautionOperation
All LEDs light up while the switch is pressed, regardless of the input
status.

Switch

ALARM
STOP

SwitchLAMP
RESET

SwitchExternal operation input
External operation input

Stop the alarm state.
LED：Flicker stop

UnusedResets (turns off) the fault indication (LED)during the manual recovery sequence.

UnusedNote (15) The sequence operation is maintained internally even during the setting mode.
Also, the switch operation is invalid, but the external operation input is valid.

(1) Operation Mode：Warning, Caution■ Automatic reset
Fault input recovers after "ALARM STOP" operation.
Instantaneous fault(20ms or less)

The display also returns automatically.

Instantaneous fault (Over 50ms)
Continued fault

Fault input (BI)Fault indication(LED)

FlickerFlicker

ALARM STOP
(Switch, BI)
LAMP RESET(Switch, BI)
LAMP TEST
Communication
output (BI)Communication
output (LED)■ Manual reset
After recovery from the fault input, the indication recovers by the "LAMP RESET" operation.
Instantaneous fault(20ms or less)Instantaneous fault (Over 50ms)
Continued fault

Fault input (BI)Fault indication(LED, Red)

FlickerFlicker

ALARM STOP
(Switch, BI)
LAMP RESET(Switch, BI)
LAMP TEST(Switch)Communication
output (BI)Communication
output (LED)10

QT-215-174(2) Operation mode：Operation
20ms or lessOver 50ms

Fault input (BI)
Status display
ALARM STOP
(Switch, BI)
LAMP RESET(Switch, BI)
LAMP TEST(Switch)Communication
output (BI)Communication
output (LED)11FSC-219-227

9 Setting mode
9.1 Setting flowchart
Control・Monitoring mode

MODE

SET

3 seconds

BI operation
mode setting

MODE

－

Sequence setting
＋

＋

＋

－

－

－

SET

MODE

SET

－

＋

Communication
output setting

Configuration

MODE

＋

SET

－

MODE

＋

SET

－

＋

BI1
operation mode

BI1
SequenceLED
brightness

AddressBI2
operation mode

BI2
Sequence

Setting
initialization

Transmission
rate

BI3
operation mode

BI3
Sequence

SoftwareversionCPU reset

BI4
operation mode

BI4
Sequence

9.2 Setting method(1) Display
Example：BI element selection■ Setting item
■ Setting element
Select with ＋,－.

(2) Operation

Example：BI1 operation mode setting■ Switch icon
Expresses that it
operates by ＋，－.
■ Current setting (ﾚ)■ Setting value
Select with ＋,－.

● Setting item / element selection display① Select the setting item / element with ＋ －. Confirm with SET .
② When confirmed, it will shift to the setting display of the selected item / element.
● Setting screen① Select the setting value with ＋ －. Confirm with SET .
② Once confirmed, the “mark (レ)” indicating the current set value will be displayed to the left ofthe changed set value.
③ When there are many setting values (address of communication output), press ＋ － for a longer time tochange at high speed.

12FSC-219-227

9.3 Setting menu
(1) BI operation mode setting BI
Thick frame：Initial setting value

Item

Setting description
Set the operation modeof fault / operation
input (BI1 to BI4).

BI operationmode

Set the lighting color
for the operation〔BI1 to BI4〕 indication.
Lighting color for
warning and caution
cannot be set.

Setting content【Operation mode】【Element】
SETMODE

The corresponding LED lights up during
setting.
<Note> "Operation" (Lighting color：Red)
has the same lighting color as"Warning". Please check theapplication before setting.

Setting range (17)WARNING (16)Red
CAUTION (16)Amber
OPERATION (WHITE) WhiteOPERATION (GREEN) GreenOPERATION (BLUE)Blue
OPERATION (RED)Red

Note(16) Initial setting value. BI1, BI2：WARNING, BI3, BI4：CAUTION
Note(17) Unit display is indicated as below.
WARNING ：MAJOR FAILURE
CAUTION ：MINOR FAILUREOPERATION：STATUS(2) Sequence setting SEQ
Thick frame：Initial setting value

Item

Setting description

Setting content【Sequence】

Sequence〔 SEQUENCE 〕

Set the sequence
operation of theannunciator.

Setting range
Automatic reset AUTO
Manual reset
MANUAL

This applies to inputs whose operation
mode is set to warning or caution.
Also, it does not affect the operation
indication.

(3) Configuration setting CFG
Thick frame：Initial setting value

Item

Setting description

Setting content【Element】【Item】

LED
brightness

Set the brightness of
the LED.

〔 LUMINANCE 〕

SET

SET

MODE

MODE

Brightness can be set for each lighting color.
Setting element
Setting range
RED
5
Bright
AMBER
4
↑
WHITE
3
GREEN
2
↓
BLUE
1
Dark
【Item】

Set value
initialization〔 DEFAULT 〕
Softwareversion【Initialization】
SET

All set values can beinitialized.

【Brightness】

MODE【After initialization】
SET

3 seconds

Press SET for 3 seconds to initialize all settings.
When initialization is complete, the "レ" mark appears on the left.
【Version】【Item】
Display the software
version.

SET
MODE〔 SOFTWARE 〕

13Version：4-digit alphanumericFSC-219-227(4) Communication output setting COM
Thick frame：Initial setting value

Item

Setting description

Setting content【Address】【Item】
Address〔 ADDRESS 〕

SET

Set the communication
address.

MODE【Item】
Transmission
rate〔 BIT RATE 〕【Transmission rate】
SET

Set the transmission
speed ofcommunication.

The equipment can bereset while power supply
CPU reset
is applied, such as
during recovery from the〔 CPU RESET 〕
communication stop
state.

MODE【Item】

Setting range
1･･･
64
Setting range
156kbps
625kbps
2.5Mbps
5Mbps
10Mbps【Reset】
SET
MODE

14

Press SET for 5 seconds
to reset the device.
(Will be in monitoringmode after reset)

FSC-219-227

10 Test mode
10.1 Test flow
Control / Monitoring mode

SET

Test mode

MODE

Press 3 seconds
MODE<Note> When in test mode, the fault / operation input becomes invalid and all sequence operations are cleared.

10.2 Test method
The sequence operation can be checked without applying input to the fault / operation input (BI1 to BI4).
Test item
Test content
・Select the fault / operation input (BI1 to BI4) to be tested with ＋ or － .
・Press SET to ON the selected BI, and press SET again to OFF the BI.
Test
SET

15

FSC-219-227

11 Specification
11.1 Rating
Item
Input
Input range and input current
Power
supplyPower supply range
and consumption VA
Inrush current(Time constant)Specification
Operation lock：1 point, ON answer：1 point, OFF answer：1 point,
Fault / operation input (BI)：4 points, ALARM STOP：1 point, LAMP RESET：1 point
Input pulse width：More than 50ms（No input for 20 ms or less） Negative common(1) 85 to 127V AC
Approx. 5mA (110V AC) (Rated voltage 100/110V AC)(2) 80 to 143V DC
Approx. 5mA (110V DC) (Rated voltage 100/110V DC)(1) 85 to 127V AC
4.5VA (Rated voltage 100/110V AC)(2) 80 to 143V DC
3 W(Rated voltage 100/110V DC)
Rated voltage 110V AC Less than 1.1A (Approx. 14ms)
Rated voltage 110V DC Less than 0.8A (Approx. 14ms)

11.2 Detailed specifications
Item

Display

LED
OLED
Contact configuration

Control
outputContact capacity

Response time
ProtocolTransmission method
Synchronous method
Transmission rate
Encoding method
Transmission path format
Transmission format
Error control method
Number of occupied stations
Remote input / output
Remote register
Maximum transmission
Communication distance
outputNumber of connections

Address setting
Connection cable
Terminating resistor

Specification
LOCAL／REMOTE：Amber, OFF：Green, ON：Red
Total 4 points, Fixed value
Warning：Red, Caution：Amber, Operation：White, Green, Blue, Red
Total 4 points, Can be set for each input.
Display guidance on settings and tests.
ON, OFF
Normally-open contact (a contact) 2 points
125V AC 8A, 125V DC 0.3A (Resistance load)
125V AC 5A, 125V DC 0.1A (Inductive load)Less than 10ms
CC-Link Ver.1.10
Broadcast polling method
Frame synchronization method
156kbps / 625kbps / 2.5Mbps / 5Mbps / 10Mbps
NRZI
Bus format (compliance standards, TIA-485-A)
HDLC compliant
CRC (X16 ＋ X12 ＋ X5 ＋1)
Remote device station. 1 station is occupied.
RX：32 points RY：32 points
RWr：4 points RWw：4 points
1200m (156kbps) / 900m (625kbps) / 400m (2.5Mbps) / 160m (5Mbps)/ 100m (10Mbps)① { (1×a) ＋ (2×b) ＋ (3×c) ＋ (4×d) } ≦ 64 stations
a：Number of units occupied by 1 stationb：Number of units occupied by 2 stations
b：Number of units occupied by 3 stations
d：Number of units occupied by 4 stations② { (16×A) ＋ (54×B) ＋ (88×C) } ≦ 2304
A：Number of connected of remote I/O stations ･･･ MAX. 64 units
B：Remote device station ･･･････････････････････ Max. 42 units
C：Number of connected of local stations and intelligent device
stations ･･････ MAX.26 units
1 to 64
Ver.1.10 compatible CC-Link dedicated cable110Ω
Internal termination resistor is connected when theterminal is short-circuited

16

FSC-219-227

Item
Insulation resistance

Voltage test
(Power frequency
withstand voltage)

Impulse voltage test
(Impulse withstandvoltage)Damped oscillatory wave
immunity test
IEC 61000-4-12
Square impulse immunity
test
B-402 Standards

Radio wave immunity test

Electrostatic discharge
immunity test
IEC 61000-4-2
Vibration
ShockPower outage guarantee
Overload capacity

Specification / Performance
Between power supply, input, control output andground (communication output is grounded).
Above 50MΩ at 500V DC.
Between power supply and input and control output.
Between control outputs.
Between power supply, input, control output andground (communication output is grounded).
2210V AC (50/60Hz) 5 seconds
Between power supply and input and control output.
Between control outputs
1390V AC (50/60Hz) 5 seconds
Between power supply, input, control output andground (communication output is grounded).
Between power supply and input, control output,
communication output.
5kV 1.2/50μs
Between input and power supply, control output,
communication output.
Between control output and power supply, input,
communication output
Peak voltage：2.5kV, frequency：1MHz ±10％, Add 3 times for 30 seconds.
Malfunction and communication stop must not occur.
・Power supply (Normal / Common)
Add noise (1μs, 100 ns width) repeatedly for 5 minutes.
Malfunction and communication stop must not occur.
・Power supply (Normal / Common)
2.0kV or more・Input (BI) (Common)
1.5kV or more・Control output (Common)
1.5kV or more・Communication output (Induction)
1.0kV or more
・There should be no malfunction or communication stop when the radio waves of
the rated output 5W transceiver (150MHz band, 400MHz band) are contacted andintermittently irradiated.
・There should be no malfunction or communication stop when the radio waves of themobile phone or wireless LAN (2.4GHz, 5GHz) are contacted and intermittently
irradiated.
Conducted under normal usage conditions.
No malfunction or communication stop at air discharge 15kV, contact discharge 8kV.
Capacitor charge method.
IEC 60068-2-6：2007
Frequency range：10 to 55 Hz, Single amplitude：0.15 mm, Sweep cycle：10 times
IEC 60068-2-27：2008
Peak acceleration：500 m/s2
Each set value is data-saved by non-volatilized memory.
1.5 times 10 seconds, 1.2 times continuation (AC power supply), 1.3 times continuation(DC power supply) of rated voltage.

Construction
Material
color
Protection rating

110×110×103.5mm [W×H×D] , Body diameter：99mmφ , With terminal coverCase：ABS (V-0) , Terminal block：PBT , Terminal cover: Polycarbonate
Black（Munsell N1.5）
IP40

Terminal screw
Mass
Operating temperatureand humidity limits
Storage temperature
limits

M4×15 ，M3×14
Approx. 500g
-10 to 55℃ , 5 to 95％ RH（Non condensing）-25 to 70℃

17

FSC-219-227

12 Trouble shooting
TroubleLED does not lights.

Probable cause
No power supply is applied toterminals 1-2
Fault / operation input is notappliedON answer, OFF answer input is notappliedEven if LAMP RESET switch ispressed (external operation
input is applied), LED does
not turn off.
OLED display does notlights.
ON control is not possible

Fault / operation input is applied

Auto display off function (Display
off without operation for 10
minutes)
ON Answer input is applied

Operation lock input is applied
Remote / Local status does not
match
Warning is display
OFF control is not possible

OFF Answer input is applied

Operation lock input is applied
Remote / Local status does not match
Warning is display
Data link error,
Communication error

Communication settings (Address,
Bit rate) are not correct
Communication cable isdisconnected or not connected
correctly (polarity, etc.)
Ver.1.10 compatible communication
cable is not used
Incorrect communication procedure
Communication is stopped
Termination resistor is notconnected

18

Treatment method
Please by applying power supply.
LED does not light when fault and status inputs
are not applied. By pressing the LAMP TEST
switch, lighting can be confirmed.
LED does not light when ON answer and OFF answer
inputs are not applied. By pressing the LAMPTEST switch, lighting can be confirmed.
LED cannot be turned off when a fault /operation input is applied.

The OLED display is lighted by entering thesetting mode or the test mode.
During ON answer input (ON LED lights), ON
control cannot be performed by the main unit
switch.
ON control cannot be performed while operation
is locked.
Remote：Operate using CC-Link communication.
Local：Operate using switch on the main unit.
ON control cannot be performed while warning
is displayed.
During OFF answer input (OFF LED lights), ON
control cannot be performed by the main unit
switch.
ON control cannot be performed while operation
is locked.
Remote：Operate using CC-Link communication.
Local：Operate using switch on the main unit.
ON control cannot be performed while warning
is displayed.
Check the setting
Check the communication cable.

Check the communication specification.
Please perform the CPU reset.
Make sure that a terminating resistor isconnected to the terminating device.

FSC-219-227

Tokyo Office : 11-13, Hitotsuya 1-chome, Adachi-ku, Tokyo, 121-8639, JAPAN.
TEL：+81-3-3885-2411 , Fax：+81-3-3858-3966
Kyoto Office : 1-19, Ichinobe-Nishikawahara, Jyoyou-shi, Kyoto, 610-0114, JAPAN.
TEL：+81-774-55-1391 , Fax：+81-774-54-1353

DATE：January 31, 202019