The New York Chelsea Data Center
Delivering Premier Connectivity in New YorkThe New York Chelsea Data Center
The New York Chelsea Data Center is strategically located in Manhattan, at 85 10th Avenue, andoffers 60,000 square feet of Tier 3 colocation space. Connected to the Telehouse owned New
York International Exchange, the Data Center provides direct access to over 25 major carriers and150 connectivity members. The colocation facility is ideal for financial, ad tech, content delivery,and managed service providers, as well as any other organizations looking to take advantage of theaccessibility and carrier density Manhattan has to offer.
• Flexible colocation options from half a cabinet up to full racks and private cages• Fully managed speedy 24/7 remote hands support• Migration and hardware supply and maintenance• Domestic and global connectivity with access to CDNetworks Media Acceleration

www.telehouse.com

The New York Chelsea Data Center
PowerFire Detection and Suppression• Standard power to rack at 3.5kVA with scalable
options to 5kVA
• Single power feed of 4.15MVA in a N+2
configuration is provided into the building• Four static 750kVA (3,000 total kVA); 3+1
configuration• Two 2.5MVA diesel-powered generators fueled toprovide 80 hrs at full load
• Battery capacity at 15 minutes at full load
• Two to four independent power circuits per
cabinet from the resilient banks of UPS on a(N+1) configuration• Gas suppression system ensures no damage tocustomer equipment• Smoke alarms with pre-action sprinklers• State-of-the-art leak sensors in place• Rooftop antenna access• 24/7 onsite Facility Engineering, TechnicalSupport & Customer Assistance CenterAir Conditioning and Cooling• Redundant N+1 cooling as 2 chiller systems with
4 risers• Maximum external ambient temperatures of75˚F and 50% humidity• Hot aisle/cold aisle zone design• Four cooling towers• Over 18 inch raised floor throughout• 24/7 central monitoring for all HVAC andbuilding systems

Security Systems• CCTV surveillance installed throughout internaland external perimeters• Secured & monitored single-person point entry
and physical 24/7 security personnel on-site• 24/7 authorized customer personnel access
via regularly updated access lists with photoidentification• Biometric security confirmation systemthroughout the facility• Separate access card required for the use ofelevators to access customer colocation floor• Strict security processes are in place to ensure
delivery and loading of goods are secure

Additional Specifications

Connectivity• Multiple bandwidth & IP connectivity options• Low monthly cross connect fees and choiceof managed IT services inside or outside ourfacilities• Diverse external and internal ﬁber routes (POEand building risers), all supported with DSR-MDFIDF high performance cabling• Peering with Telehouse America’s InternationalInternet Exchanges allows you to interconnect
to multiple transit providers versus connecting
individually• Both NYIIX and LAIIX are based on Brocade
carrier class and high speed platform. Public
and/or private peering via VLAN services
are available. Route servers are available atboth locations.

••••Over 18 inch raised floor throughout
8.85 ft. above raised floor
Maximum floor load of 143.4 lb/sq. ft.
Overhead power and communications
cable route• Current PUE level at 1.69
• Customer staging rooms available withstorage space• Access to rooftop antenna available

www.telehouse.com