DP3000G

GRAPHIC PROGRAM SETTER
DP3000G series is a graphic program setter
employed high visibility 5.6" TFT color LCD
display. Maximum 200 types of program
pattern (Maximum 4000 steps) are stored andperformance pattern is selectable. Setting
output can be selected from high accuracy
analog output (DC current/ voltage) and digital
output with no setting errors usingcommunications.

■ FEATURES■ MODELS●Employing clear 5.6" TFT color LCD display

D P3−□0 G□0 0−□□□Graphic screen of pattern progress status, display of PV

Setting output signal

value/SV value/pattern/step/time and various monitor func-

1 : Digital output (RS422A)

tions such as enlarged data display and external input/out-

2 : Analog output (4 to 20mA)
4 : Analog output (0 to 10V)

put status display are prepared.

5 : Analog output (0 to 1V)●Easy program pattern settings on graphic screen

7 : Digital output (RS485)
Communications interface *1

Maximum 200 patterns /Maximum 4000 steps settings,

0 : Nonepattern repeat, linking between patterns and endless pro-

R: RS232C (COM1) * 2 OPgram setting are available.

S : RS485 (COM1)* 2 OP●Time signal settings per stepA : RS422A (COM1) *2 OPTime signal 30 types are selectable. Maximum 28 points

B : RS232C (COM1) + RS232C (COM2) *2 OP
C: RS485 (COM1) + RS232C (COM2) *3 OP

external output assignment is available.

D: RS422A (COM1) + RS232C (COM2) *4 OP●Storing settings in CF card

E : RS232C (COM1) + RS485 (COM2) *2 OP

Setting management is easy as all settings including set-

F : RS485 (COM1) + RS485 (COM2) *3 OPting program pattern and each parameter are stored in CG: RS422A (COM1) + RS485 (COM2) *4 OP
Case color

F card and readout from it.

G: Gray

PC software allows you to edit program pattern and para-

B : Black OP

meter.

External input / output signal●Abundant external input / output functions

0 : None OP

Remote contact, pattern selection, time signal and status

1 : Digital input/ output (non voltage contact input)
2 : Digital input/ output

signal output are available by digital input/output function.

(External power supply spec for only input) OP

Unit with external input 16 points and external output 28Transmitter power supply

points enables function assignment setting.

0 : None
1 : Transmitter power supply OP

OP : Option*1 Rear port exclusive use for COM1, front and rear port switchable for COM2.
*2 Option cannot be selected when setting output is 1 or 7 (digital output).
*3 COM1 is setting output when setting output is 7 (RS485).
Option cannot be selected when setting output is 1 (RS422A).
*4 COM1 is setting output when setting output is 1 (RS422A).
Option cannot be selected when setting output is 7 (RS485).

1PSE-363A

DP3000G■ OPERATION SCREEN●Running status display at once
Running status display of pattern progress, SV, time andtime signal.

●Enlarged data screen
Enlarged display of SV and elapsed time (or remainingtime).

●External input status display screen●External output status display screen●Program pattern setting screen■ KEY ARRANGEMENT

A/M

RUN

RESET

DISP

ESC
Direction key

FNC

STOP

ADV

MENU

ENT2Mode 10 (Enhanced setup)
Mode 11 (Maintenance)
Mode 12 (Help)Operation:
Operation start/stop (RUN/STOP), operation reset(RESET), stepping operation (ADV), fast-forwarding (FAST)
Display operation: Switching between operation screens
HOME screen (registered operation screen)
automatic display
Engineering port: Serial port on the front panel(Custom cable connection)■ PROGRAMMING SPECIFICATIONSPattern set type:

Target temp(SV)/Time or Ramp rate/TimeTime setting − Hour/Minute or Minute/Second
Ramp rate setting − Temperature/Minute orTemperature/Second
Number of steps: Up to 199 steps per pattern
Number of patterns:Up to 200 patterns
Total number of steps:Up to 4000 steps
Repeat:Pattern --- Up to 9999 times, Step --- up to 99 times
Step setup range: Target value --- Scale range
Time --- 0 to 999 hours 59 minutes or 0 to 999 minutes 59
seconds
Start temperature: Arbitrary set value start
Target value (SV) correction:−99999 to 99999, decimal point linked with scaling
Fast-forward:
Program fast-forward function provided(FAST)(Approx 10 times or 60 times)
Sequence setting: Registration per step・SV NO. 0,1 to 8
・Time signal 30 types, all ON, all OFF, antiphase, step
repetition
Progressing settings change:
Target value, time, ramp rate, SV correction
Additional function:Pattern link, circle step function, pattern edit (copy, delete)■ MEMORY CARD SPECIFICATION (Card is optional)
Memory media:
Memory size:
Saved data:
Function:■ GENERAL SPECIFICATION
Rated power voltage:100 to 240V AC 50/60Hz (universal power supply)
Maximum power consumption:30VA
Reference operation condition:
Ambient temperature humidity range --21 to 25℃, 50 to 60%RH
Power voltage --- 100V AC ±1.0%
Power frequency --- 50/60Hz ±0.5%
Attitude --- Left / right ±3°, forward/backward ±3°
Warm-up time --- 30 minutes or more
Normal operation condition:
Ambient temperature humidity range --−10 to 50℃, 10 to 90%RH
Power voltage --- 90 to 264V AC
Power frequency --- 50/60Hz ±2%
Attitude --- Left / right ±10°
, forward/ backward ±10°Transportation condition:
At the packed condition on shipment from our factory
Ambient temperature humidity range --−20 to 60℃, 5 to 90%RH
Vibration --- 10 to 60Hz 0.5G (4.9m/s2) or less
Impact --- 40G (352m/s2) or less
Storage condition: Ambient temperature humidity range --- −20 to 60℃, 5 to90%RH(No dew condensation)
Power failure protection:
The settings are kept using EEPROM and lithium
battery backed up RAM
Insulation resistance:Between secondary terminal and protection conductor
terminal --- 500V DC 20Ω or more
Between primary terminal and protection conductor
terminal --- 500V DC 20Ω or more
Between primary terminal and secondary terminal --500V DC 20Ω or more
Withstand voltage: Between secondary terminal and protection conductor
terminal --- 500V AC for 1minuteBetween primary terminal and protection conductor
terminal --- 1500V AC for 1minuteBetween primary terminal and secondary terminal --2300V AC for 1minuteProtection:
Conformed to IP54
Case assembly material:
Case, Front bezel, --- Fire-retardant polycarbonate resin
External input/output and communications terminal board--- PBT
Color:
Front bezel, case --- Gray or black
Terminal cover:Standard provision
Weight:Approx 1.6kg
Mounting:
Panel mounting
Terminal screw:
M3.5 (M3 for external input/output, setting output,communications terminal board)■ OUTPUT SIGNAL SPECIFICATION
Output renewal period:0.1 sec
Output accuracy ratings: ±0.1% of output span
Output resolution: Approx 1/50000Output types:
Analog output --- 4 to 20mA DC, 0 to 1VDC, 0 to 10VDC
Digital output --- RS422A, RS485*Thermoelectromotive equivalent output is not prepared■ EXTERNAL OUTPUT SIGNAL SPECIFICATION
Number of output: 28 points (function assignable per point)
Output type:Open collector output (24V DC, up to 50mA)
Time signal output:Default assignment --- 18 points
Output type --- ALL-ON/ ALL-OFF/ maximum of 30 types
per step
Status output:
Default assignment --- 10 points
Output type --- RUN/STOP, ADV, RESET, WAIT, FAST, END,ERR, SV-UP, SV-DOWN
Selective assignment --- Pattern/ step No.-BCD output■ EXTERNAL INPUT SIGNAL SPECIFICATION
Number of inputs: 16 points (function assignable per point except externaldrive input)
Input type:
Non voltage contact (contact capacity 12V DC, 2mA ormore)
External power supply specification 12/24V DC ON whenpower is applied (up to 12mA/point)
External drive input:Default assignment --- 5 points
Input type --- RUN/STOP, ADV, RESET, WAIT, FAST
Selective assignment --- SV holdPattern select input:Default assignment --- 10 points
Input type --- 10 types of 1, 2, 4, 8, 10, 20, 40, 80, 100, 200
Selection method --- Select the number from 1 to 200 using
BCD code■ DISPLAY SPECIFICATION
Screen:
Display content:

LCD backlight:

Compact flash (CF) card
Up to 2 GB
Setup parameters, program patterns, all data(for auto loading)
Save/read/delete/verify
For program patterns, individual or all pattern save/delete
selectable
Card format (simple format)

5.6" TFT color LCD
Operation screen
Home screen --- Pattern progress, pattern/step No.,target value, status, elapsed time or remaining time,time signal
Enlarged data screen, DO display, DI display
Setting screen
Pattern/sequence setting, time signal, memory cardmanagement, maintenance, communications, settingchange during operation
4 brightness adjustment levels■ OPTION SPECIFICATION●Transmitter power supply (Insulation type)
Power voltage:
Current capacity:■ SETTING AND OPERATION SPECIFICATION

24V DCUp to 30mA

●Communications interface

Operation key type: MENU, DISP, DIRECTION key, ENT, ESC, FNC, RUN,STOP, ADV, RESET
Setting and operation method:
Setting --- Menu calling/ cursor selection method
Operation --- Direct key operation (combined with FNC)
Menu setting:Mode 0 (Execution steps setting)Mode 1 (Operation status selection)
Mode 2 (Pattern and sequence)
Mode 5 (Setting output)
Mode 6 (Time signal)
Mode 8 (Communications setup)
Mode 9 (Memory card management)

Number of communications points:Up to 2 points
Communications type:RS232C, RS422A, RS485*COM1 is setting output for digital output*COM2 for front and rear port switching
Protocol:MODBUS/PRIVATE■ SOFTWARE
DP-G parameter editing software
・Program pattern editing / file management / printing
・Setting parameter editing / file management / printing
・CF card reading / storing for DP-G

3

■ TERMINAL ARRANGEMENT
100-240V AC

123A

B C D

DO terminals

E F G HIJOutput (+) terminal
Output (-) terminal

1516

1

Transmitter power supply terminals(option)Time signal
2

Status3

External drive/ pattern selection/ DI terminals
45
6

Setting output (digital) and communications interface (option) terminals
COM2
COM1
Terminal RS232C RS485 RS422A
Terminal RS232C RS485
6E
6I
RDSARDSA
RDA
6F
6J
SD
SB
SD
SB
RDB
6G
5J
SG
SG
SGSGSDA6HSDB*COM1 is used for setter digital output
5J
SG*RS422A: 1 port in COM1 only
*COM1 is exclusive use for rear port,rear port and front port switchable for COM2.

Setting output (analog) (-) terminal
Setting output (analog) (+) terminal■ EXTERMINAL INPUT/OUTPUT TERMINALSTime signal output terminals

Status output terminals

COM：1A ○TS 1 ：1B ○ ［LOAD］
TS 2 ：1C ○ ［LOAD］
TS 3 ：1D ○ ［LOAD］
TS 4 ：1E ○ ［LOAD］
TS 5 ：1F ○ ［LOAD］
TS 6 ：1G ○ ［LOAD］
TS 7 ：1H ○ ［LOAD］
TS 8 ：1I ○ ［LOAD］
TS 9 ：1J ○ ［LOAD］
COM：2A ○TS10：2B ○ ［LOAD］
TS11：2C ○ ［LOAD］
TS12：2D ○ ［LOAD］
TS13：2E ○ ［LOAD］
TS14：2F ○ ［LOAD］
TS15：2G ○ ［LOAD］
TS16：2H ○ ［LOAD］
TS17：2I ○ ［LOAD］
TS18：2J ○ ［LOAD］

COM ：3A ○RUN/STOP ：3B ○ ［LOAD］
ADV ：3C ○ ［LOAD］
RESET ：3D ○ ［LOAD］
WAIT ：3E ○ ［LOAD］
FAST ：3F ○ ［LOAD］
END ：3G ○ ［LOAD］（NC）：3H ○ ［LOAD］
ERROR ：3 I ○ ［LOAD］
SV・UP ：3 J ○ ［LOAD］
SV・DOWN ：4 J ○ ［LOAD］

External drive input terminals and pattern selection input (BCD code) terminals
External drive signal
COM ：4A ○RUN/STOP：4B ○ADV：4C ○RESET：4D ○WAIT：4E
FAST：4F ○（BLK）：4G ○BCD code 100：4H ○200：4 I ○COM：5A ○1：5B ○
2：5C ○
4：5D ○
8：5E ○
10：5F ○
20：5G ○
40：5H ○
80：5 I ○*COM: Common to time signal output

COM ：4A ○RUN：4B ○STOP：4C ○RESET：4D ○ADV：4E ○（BLK）：4F ○（BLK）：4G ○100：4H ○200：4 I ○12V/24V
COM：5A ○1：5B ○
2：5C ○
4：5D ○
8：5E ○
10：5F ○
20：5G ○
40：5H ○
80：5 I ○*External power supply spec
Applicable to equivalent of DP-I spec

■ DIMENSIONS

14417223
235252138 ＋01

170

170

159

144137×137● PANEL CUTOUT

138 ＋01

Unit: mm

Specifications subject to change without notice. Printed in Japan (I) 2018. 832-8 KUMANO-CHO,ITABASHI-KU,TOKYO 173-8632
Telephone : +81-3-3956-2171
Facsimile : +81-3-3956-0915
E-mail : inter@chino.co.jp
Website : www.chino.co.jp/"