SE3680H, SE4000H, SE5000H, SE6000H

12-25

YEAR
WARRANTY

INVERTERSEV Charging Single Phase
Inverter2-in-1 EV Charger and Solar Inverter, Speeds Up Installationand EV Charging
Combines solar and grid power for EV charging
up to 2.5 times faster than a typical mode 2charger
Maximizes self-consumption and optimizes useof renewable energy
Designed to work specifically with SolarEdge
Power Optimizers
Record-breaking efficiency with 200% DC
oversizing
Built-in module-level monitoring

solaredge.com

Compact, lightweight, and as easy to install andcommission as a standard SolarEdge inverter
Easy wireless connectivity to system devices via
optional SolarEdge Energy Net platform
Flexible selection of charger cable types and lengths(cable and holder ordered separately)
Built-in 6mA DC-RCD, compliant with IEC
62752:2016, for reduced labor and installation cost

EV Charging Single Phase Inverter
SE3680H, SE4000H, SE5000H, SE6000H
INVERTER SPECIFICATIONS:

SE3680H

SE4000H

SE5000H

SE6000H

Rated AC Power Output

3680

4000

5000(1)

6000

Maximum AC Power Output

3680

4000

5000(1)6000

OUTPUT — AC (LOADS / GRID)VAVA

AC Output Voltage (nominal)

220 / 230

VacAC Output Voltage Range

184 - 264.5

VacAC Frequency (nominal)

50 / 60 ± 5

Maximum Continuous Output Current
Maximum Output Fault Current and Duration

Hz1618.5

2327.5A

16 / 20

18.5 / 20

23 / 2027.5 / 20

A / msResidual Current Detector /Residual Current Step Detector

300 / 30mA

Inrush current AC (Peak / Duration)

2.8 / 20

Aac (rms)
/ ms

38

A

Maximum Output Over Current Protection
Power Factor Range

1 (adjustable from -0.9 to +0.9)

Total Harmonic dDstortion<3Protective ClassClass I

Utility Monitoring, Islanding Protection, Country
Configurable Thresholds

Yes

Overvoltage Category

III

INPUT — DC

Maximum DC Power

7360%

8000

Transformer-less, Ungrounded

10000

12000

W

Yes

Maximum Input Voltage

480

Vdc

Nominal DC Input Voltage

380

Vdc

Maximum Input Current

10.5

11.5

Reverse-Polarity Protection

13.5

16.5

Adc

Yes

Ground-Fault Isolation Detection

600kΩ Sensitivity

Maximum Inverter Efficiency

99.2

European Weighted Efficiency

99%

Nighttime Power Consumption

< 2.5

W

ADDITIONAL FEATURES
Supported Communication Interfaces

RS485, Ethernet, Wi-Fi (requires antenna)(2), wireless SolarEdge Energy Net (optional)(3),
ZigBee for Smart Energy (optional)(4), Cellular (optional)

Smart Energy Management
Inverter Commissioning%

Export Limitation and Excess Solar Charging(5)With the SetApp mobile application using built in Wi-Fi access point for local connection

Arc Fault Protection

Integrated, User Configurable (According to UL1699B)

STANDARD COMPLIANCE
Safety - Inverter

IEC-62109-1/2

Grid Connection Standards

UTE C15-712, G98, G99, CEI-021, EN 50438, IEC 61727, IEC 62116, ÖNORM, TF3.2.1,C10-11, NRS 097-2-1, , VDE-AR-N-4105, VDE 0126-1-1, AS-4777

EmissionsIEC61000-6-2, IEC61000-6-3, IEC61000-3-11, IEC61000-3-12, FCC Part 15 Class B

RoHSYes

AC Output — Supported Cable Diameter9 - 16mm

AC — Supported Wire Cross Section

1 - 13mm2

INSTALLATION SPECIFICATIONSDC Input(6)1 x MC4 pair

Dimensions with Connection Unit (H x W x D)
Weight with Connection Unit

2 x MC4 pair
450 x 370 x 174

1011.4Noise<25Cooling

Natural Convection

Operating Temperature Range
Ambient Air Pressure
Protection Rating

mm11.9-40 to +60(7)Minimum 860hPa - 1060hPa
IP65 — Outdoor and Indoor (inverter with connection unit)(1) 4600VA in Germany(2) Wi-Fi connectivity requires an external antenna. For more information refer to: https://www.solaredge.com/sites/default/files/se-wifi-zigbee-antenna-datasheet.pdf(3) For more information, refer to: https://www.solaredge.com/sites/default/files/se-energy-net-plug-in-datasheet.pdf(4) For more information refer to: https://www.solaredge.com/sites/default/files/se-zigbee-plug-in-wireless-communication-for-setapp-datasheet.pdf(5) Import/Export meter is required for Export Limitation and for controlled Excess Solar charging(6) Connection of additional strings in parallel to a single input is allowed as long as the cumulative current does not exceed 45A(7) Full power up to at least 50°C. For power de-rating information refer to: https://www.solaredge.com/sites/default/files/se-temperature-derating-note.pdf

kgdBA
˚C

EV Charging Single Phase Inverter
SE3680H, SE4000H, SE5000H, SE6000H
EV CHARGER AND EV CHARGER CABLE SPECIFICATIONS:OUTPUT — AC (EV CHARGER)
AC Mode 3
Connection to the SolarEdge monitoring platform is required for first EV chargingCharging Mode
Minimum Charge Rate(7)

1.5

kW

Rated AC Power Output (grid & PV)

7400

W

Nominal AC Output Voltage

230

Vac50 / 60

HzMaximum Continuous Output Current @230V(grid & PV)

32

Aac

Residual Current Detector (AC)30mA rms

Residual Current Detector (DC)6mAdc

Nominal AC Frequency

ADDITIONAL FEATURESEV Charger Status LEDs, Fault Indicator
EV Charger Ground Connection Monitoring
EV Charger Configuration
EV Charger Unplugging Detection

Yes
Yes, continuous
Via the monitoring app; Ethernet, Wi-Fi or ZigBee connection is required(8)Yes, current termination according to IEC62196

STANDARD COMPLIANCE
SafetyIEC 61851, IEC 62752:2016

EV Charger

IEC 62196

INSTALLATION SPECIFICATIONSEV Charger Connector

IEC 62196 Type 1 or Type 2

EV Charger Cable Length(9)7.6 (4.5 option)m

EV Charger Cable Weight

5.7 (3.5 for 4.5m option)kg-30 to +50

˚C

EV Charger Cable Operating Temperature Range
Protection Rating (connected to EV or with dust cap)

IP54(8) Minimum charge rate is in compliance with IEC61851-1 and J1772™ FEB2016 standards.
(9) Cellular connection may be used; requires a SIM card with a 1GB data plan that should be purchased from a cellular provider(10) EV charger cable ordered separately© SolarEdge Technologies Ltd. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdge
Technologies, Inc. All other trademarks mentioned herein are trademarks of their respective owners. Date: 12/2021 DS-000120-1.0-ENG. Subject to change without notice.