For Short PV Strings
SE3K-RWB / SE4K-RWB / SE5K-RWB

12-25
YEAR
WARRANTY

INVERTERS

Three Phase Inverter

The ideal solution for small-scale residential PV systems
Greater design flexibility by enabling significantly
shorter strings for low power three phase PV systems

Excellent reliability with standard 12-year
warranty (extendable to 20 or 25 years)

Optimized for installations with complex roofs(multi-facets and different orientations)

Advanced safety features, including touch-safe DC
voltage when the inverter is off or disconnected

Supports optional smart energy devices andexpansion of system capabilities

Quick inverter commissioning directly from theSetApp smartphone app

Single vendor solution for seamless operation ofall system components, and one address forwarranty and service issues
Built-in module-level monitoring for greater
visibility into system performancesolaredge.com

Suitable for outdoor or indoor installations

Three Phase Inverter
SE3K-RWB / SE4K-RWB / SE5K-RWB
SE3K-RWBTEBEN4

SE4K-RWBTEBEN4

SE5K-RWBTEBEN4UNITS

Rated AC Power Output

3000

40005000

VAMaximum AC Power Output

300040005000VA

APPLICABLE TO INVERTERS WITH PART NUMBER
OUTPUT

AC Output Line Connections

3-phase, 4-wire / PE (L1-L2-L3-N), TN, TT

AC Output Voltage - Line to Line / Line to Neutral (Nominal)
AC Output Voltage - Line to Neutral Range
AC Frequency
Maximum Continuous Output Current (per phase)5

Grid Supported - Three Phase

380/220; 400/230

Vac

264.5

Vac

50/60 ± 5 %

Hz

6.5

8A

6750

W

3 / N / PE (WYE with Neutral)

Utility Monitoring, Islanding Protection, Configurable Power Factor,
Country Configurable Thresholds

Yes

INPUT
Maximum DC Power (Module STC)

4050

5400

Transformer-less, UngroundedYes

Maximum Input Voltage

450

Vdc

Nominal DC Input Voltage

375

Vdc

Maximum Voltage to Earth450

Vdc

Maximum Input Current

8.5

Reverse-Polarity ProtectionAdc

350 kΩ sensitivity

Maximum Inverter Efficiency
Night-time Power Consumption

14Yes

Ground-Fault Isolation Detection
European Weighted Efficiency

11.5

97.8
94.6

%

95.7

96.3

<4%
W

ADDITIONAL FEATURES
Supported Communication Interfaces(1)2 x RS485, Ethernet, Wi-Fi(2), ZigBee for Smart Energy (optional), Cellular (optional)

Inverter Commissioning

With the SetApp mobile application using built-in Wi-Fi station for local connection

Smart Energy Management

Export Limitation, Home Energy Management (Device Control)

STANDARD COMPLIANCE
SafetyGrid Connection Standards
Electromagnetic Compatibility (EMC)
RoHS

IEC-62109-1/2
EN 50549-1
EN/IEC 61000-6-1, EN/IEC 61000-6-2, EN/IEC 61000-6-3, EN/IEC 61000-6-4, EN 55011,
FCC Part 15, EN/IEC 61000-3-2, EN/IEC 61000-3-3, EN/IEC 61000-3-11, EN/IEC 61000-3-12
Yes

INSTALLATION SPECIFICATIONSAC Output

Cable gland diameter 15-21

DC Input

2 x MC4 pair

Dimensions (H x W x D)

540 x 315 x 260mm

24.5kgWeightOperating Temperature Range
Cooling
Noise
Protection Rating
Mounting
Number of Power Optimizers per String
Maximum Power per String-40 to +60(3)mm°C

Fan (user replaceable)< 50dBA

IP65 - outdoor and indoor
Brackets provided
8(4)/9 to 205625(1) Refer to Datasheets -> Communications category in Resources Library for specifications of optional communication options: https://www.solaredge.com/downloads#/(2) Wi-Fi connectivity requires an external antenna. For more information refer to: https://www.solaredge.com/sites/default/files/se-wifi-zigbee-antenna-datasheet.pdf(3) For power de-rating information refer to: https://www.solaredge.com/sites/default/files/se-temperature-derating-note.pdf(4) When using P404/P485/P505 power optimizers only, minimum required per string is eight© SolarEdge Technologies, Ltd. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdge Technologies, Inc.
All other trademarks mentioned herein are trademarks of their respective owners. Date: June 16, 2022 DS-000042-ENG. Subject to change without notice.

W