Page

Number

1/54

QG18720

μGPCsH Series

Industry Business Division

User’s Manual Hardware

Issuing department

SymbolDate

Product
name-2010.10.28

Industrial Plant
Development Group

HistoryFirst issue

Page

Approved

CheckedCreatedUser’sManual Hardware–
レ
Onituka
Onituka

TOYO DENKI SEIZO K.K.

Page 2/ 54 Symbol
Sym
QG18720
Numberbol

PrefaceThank you for purchasing the Toyo Denki FA μGPCsH digital controller. The μGPCsH Series User’s Manual(Hardware) explains the system configuration, the hardware specifications of the modules, and theiroperation. In order to use the μGPCsH correctly, please read this manual carefully.
Please also read the related manuals below.

Name

NumberContent

μGPCsH Series Programming
Manual (Instruction Words)

QG18273

μGPCsH Series memory, language, systemdefinitions etc.

μGPCsH Series User’s Manual(Operation)

QG18291

Explains the interface of TDFlowEditor and how to
use the program

SHPC-172 Operation Manual (PGemulator module)

QG18262

Explains operation of the PG emulator module

SHPC-861 Operation Manual(Pulse output module)

QG18393

Explains operation of the pulse output module

SHPC-161 Operation Manual(Versatile communications module

QG18381

Explains operation of the versatilecommunications module

SHPC-193 Operation Manual(OPCN-1 I/F module)

QG18356

Explains operation of the OPCN-1 I/F module

Caution(1) No part of this manual may be reproduced or duplicated without permission.
(2) The content of this manual is subject to change without prior notice.
(3) We have endeavored to make this manual as complete and accurate as possible. However, if you
notice any errors or ambiguities, please report them to the sales office shown on the back of thismanual, stating the manual number indicated on the front cover.

2

Page 3/ 54 Symbol
Sym
QG18720
Numberbol

Safety Notice
Read the “Safety Notice” carefully before using the product and use the product accordingly. In this manual,safety-related items are divided into “Danger” and “Caution” as follows.
Danger: Mishandling may cause death or serious injury.
Caution: Mishandling may cause moderate bodily injury, minor injury or damage to property.
Note that items marked
circumstances.

Caution may also result in other serious consequences depending on the

All safety notices contain important information which should be strictly observed. Matters requiring special
attention are shown below, which are also indicated with the marks shown above.
Danger Do not touch live parts such as terminals, etc., while electricity is on. Doing so may result in electric shock.
 Shut off the power supply before performing mounting, dismantling, wiring, maintenance and inspection
work. Working with the power on may result in electric shock, and malfunction or failure of the machinery.
 Emergency stop circuits, interlock circuits, etc., must be built into the equipment, not the PC. Otherwise,
malfunction of the PC may result in damage or accidents involving the machinery.
 Batteries must not be connected with + - terminals placed backward, recharged, dismantled, subjected topressure or other force, thrown into fire, or short-circuited. Doing so may result in rupture of the batteries orfire.
 If the batteries are damaged, leaking or otherwise faulty, do not use them. Doing so may result in ruptureof the batteries or fire.
 Never open the FG terminal with LG - FG short-circuited. Doing so may result in electric shock. (Groundthe wire without fail.)3

Page 4/ 54 Symbol
Sym
QG18720
Numberbol
Caution If any articles are found to be damaged or out of shape when you unpack them, do not use them. Doing so
may result in fire, malfunction or failure of the machinery.
 Do not subject the product to shock by letting it drop or fall over. Doing so may damage the machinery orcause it to malfunction.
 The product must be installed in accordance with the operating instructions and manuals. Improper
installation may cause the product to fall down, malfunction or otherwise fail.
 Use the product with the rated voltage and current indicated in the operating instructions and manuals.
Using the product with other values may result in fire, malfunction or failure of the machinery.
 The product must be used or stored under the environment indicated in the operating instructions andmanuals. Using or storing the product in environments with high temperatures, high humidity,
condensation, dust, corrosive gasses, oil, organic solvents, and significant vibration or shock may result inelectric shock, fire, malfunction or failure.
 Select electric wires of the right size for the voltage and current used. They must be tightened with thespecified torque. Improper wiring and tightening may result in fire and may cause the product to fall down,
malfunction or otherwise fail.
 Perform installation work taking care to prevent foreign matter such as packaging, scraps of electric wires,
iron filings, etc., from getting inside the equipment. Foreign matter in the machinery may result in fire,malfunction or failure of the machinery.
 Grounding terminals must be grounded without fail. Failure to ground terminals may cause electric shockor malfunction.
 Screws for terminals and screws for installation must be checked at regular intervals to ensure that they
are securely tightened. Loose screws may result in fire or malfunction.
 Unused connectors should be covered with the connector covers provided. Failure to do so may result in
malfunction or failure.
 Terminal blocks must be covered with terminal covers. Failure to do so may cause electric shock or
malfunction.
 Only perform operations such as changing programs, forced output, start, stop, etc., after ensuring safety.
Incorrect operation may cause the machine to function, resulting in accidents or damage to the machinery.
 Tool interface connectors must be inserted in the proper direction. Failure to do so may cause malfunction.
 Before touching the PC, discharge static electricity by touching grounded metals, etc. Excessive static
electricity may cause malfunction or failure of the PC.
 Wiring must be performed correctly in accordance with the operating instructions and manuals. Incorrect
wiring may result in fire, malfunction or failure of the machinery.
 When removing a plug from its socket, do not pull on the cord. Damage to the cable may result in fire or
failure of the machinery.
 Do not change the system by attaching or detaching I/O modules etc. with the power turned on. Changing
the system with the power on may result in malfunction or failure.
 The product must never be repaired onsite. If repairs are required, please contact Toyo Denki. In addition,
when replacing batteries, ensure that the connectors are attached to the correct terminals. Failure to do so
may result in fire, accident, or failure of the machinery. When cleaning the machinery, turn off the power.
 Use a cloth moistened with warm water. Using thinner or other organic solvent may cause melting or
discoloration of the surface of the machinery.
 Do not modify or dismantle the product. Doing so may result in failure of the machinery.
 When discarding the product, it should be handled as industrial waste.
 This product is not designed or manufactured for use in equipment or systems that involve the safety ofhuman life.
 If you intend to use this product for special purposes such as controlling atomic energy, for aviation andaerospace, medicine, transportation equipment, transportation vehicles, or for related systems, please
consult our sales representative.
 If this product is used with equipment that is expected to involve the safety of human life or serious losses
as a result of failure of the equipment, safety devices must be installed.
 The external power supply (DC 24 V power supply etc.) connected to the DC I/O must use a power supply
with reinforced insulation from an AC-based power supply. (We recommend using a power supply thatcomplies with EN60950.) Failure to do so may result in accident or failure of the machinery.
4Page 5/ 54 Symbol
Sym
QG18720
Numberbol

History of Revisions* The manual number is shown at the bottom right of the cover sheet.

Date printed* Manual number

Details of revision

2010.10

QG18720First edition issued

5

Page 6/ 54 Symbol
Sym
QG18720
Numberbol

Contents
PREFACE ................................................................................................................................................................2
SAFETY NOTICE ....................................................................................................................................................3
HISTORY OF REVISIONS ......................................................................................................................................5
CONTENTS .............................................................................................................................................................6
CHAPTER 1

OUTLINE ........................................................................................................................................8

1.1
MODEL LIST ................................................................................................................................................8
1.1.1
Hardware............................................................................................................................................8
CHAPTER 2

SYSTEM CONFIGURATION .......................................................................................................10

CHAPTER 3

SPECIFICATION ..........................................................................................................................11

3.1
GENERAL SPECIFICATIONS .........................................................................................................................11
3.2
POWER SUPPLY MODULE SPECIFICATIONS .................................................................................................123.2.1
Power Supply Specifications............................................................................................................12
3.2.2
Name of Each Part and its Function ................................................................................................13
3.3
STANDARD CPU MODULE SPECIFICATIONS ................................................................................................14
3.3.1
Performance Specification List ........................................................................................................14
3.3.2
Name of Each Part and its Function ................................................................................................15
3.3.3
CompactFlash Card Operation ........................................................................................................18
3.3.3.1
Operation from the CPU Module ..............................................................................................18
3.3.3.2
Saving to CompactFlash Card ..................................................................................................18
3.3.3.3
Errors when Reading and Writing CompactFlash Card ...........................................................19
3.4
BASEBOARD SPECIFICATIONS.....................................................................................................................20
3.4.1
Performance Specification List ........................................................................................................20
3.5
INDIVIDUAL SPECIFICATIONS OF THE DIGITAL INPUT MODULE .......................................................................21
3.5.1
DC 24 V Input 16 Points ..................................................................................................................21
3.5.1.1
Performance Specification List .................................................................................................21
3.5.1.2
Name of Each Part and its Function .........................................................................................22
3.5.1.3
External Connection .................................................................................................................22
3.5.1.4
Internal Circuit ...........................................................................................................................22
3.5.2
DC 24 V Input 32 Points ..................................................................................................................23
3.5.2.1
Performance Specification List .................................................................................................23
3.5.2.2
Name of Each Part and its Function .........................................................................................24
3.5.2.3
External Connection .................................................................................................................24
3.5.2.4
Internal Circuit ...........................................................................................................................24
3.5.3
DC 24 V Input 64 Points ..................................................................................................................25
3.5.3.1
Performance Specification List .................................................................................................25
3.5.3.2
Name of Each Part and its Function .........................................................................................26
3.5.3.3
External Connection .................................................................................................................26
3.5.3.4
Internal Circuit ...........................................................................................................................26
3.5.4
AC 100 V Input 16 Points .................................................................................................................27
3.5.4.1
Performance Specification List .................................................................................................27
3.5.4.2
Name of Each Part and its Function .........................................................................................28
3.5.4.3
External Connection .................................................................................................................28
3.5.4.4
Internal Circuit ...........................................................................................................................28
3.6
INDIVIDUAL SPECIFICATIONS OF THE DIGITAL OUTPUT MODULE ...................................................................29
3.6.1
Transistor Output 16 Points .............................................................................................................29
3.6.1.1
Performance Specification List .................................................................................................29
3.6.1.2
Name of Each Part and its Function .........................................................................................30
3.6.1.3
External Connection .................................................................................................................30
3.6.1.4
Internal Circuit ...........................................................................................................................30
3.6.2
Transistor Output 32 Points .............................................................................................................31
3.6.2.1
Functional Specification List .....................................................................................................31
3.6.2.2
Name of Each Part and its Function .........................................................................................32
3.6.2.3
External Connection .................................................................................................................32
3.6.2.4
Internal Circuit ...........................................................................................................................32
6

Page 7/ 54 Symbol
Sym
QG18720
Numberbol
3.6.3
Transistor Output 64 Points .............................................................................................................33
3.6.3.1
Functional Specification List .....................................................................................................33
3.6.3.2
Name of Each Part and its Function .........................................................................................34
3.6.3.3
External Connection .................................................................................................................34
3.6.3.4
Internal Circuit ...........................................................................................................................34
3.6.4
Relay Output 16 Points ....................................................................................................................35
3.6.4.1
Functional Specification List .....................................................................................................35
3.6.4.2
Name of Each Part and its Function .........................................................................................36
3.6.4.3
External Connection .................................................................................................................36
3.6.4.4
Internal Circuit ...........................................................................................................................36
3.7
INDIVIDUAL SPECIFICATIONS OF THE DIGITAL I/O MIXED MODULE ................................................................37
3.7.1
DC 24 V Input 32 Points, Output 32 Points .....................................................................................37
3.7.1.1
Performance Specification List .................................................................................................37
3.7.1.2
Name of Each Part and its Function .........................................................................................39
3.7.1.3
External Connection .................................................................................................................39
3.7.1.4
Internal Circuit ...........................................................................................................................39
3.8
ANALOG INPUT: 8 CHANNELS .....................................................................................................................40
3.8.1
Functional Specification List ............................................................................................................40
3.8.2
Name of Each Part and its Function ................................................................................................40
3.8.3
External Connection .........................................................................................................................41
3.8.4
Scaling .............................................................................................................................................42
3.9
ANALOG OUTPUT: 4 CHANNELS ..................................................................................................................43
3.9.1
Functional Specification List ............................................................................................................43
3.9.2
Name of Each Part and its Function ................................................................................................43
3.9.3
External Connection .........................................................................................................................44
3.9.4
Scaling .............................................................................................................................................45
3.10 COMMUNICATION MODULE INDIVIDUAL SPECIFICATIONS ..............................................................................46
3.10.1 Versatile Communications Module ..................................................................................................46
3.10.1.1 Functional Specification List .....................................................................................................46
3.10.1.2 Name of Each Part and its Function .........................................................................................46
3.10.2 OPCN-1 Master Module ...................................................................................................................47
3.10.2.1 Functional Specification List .....................................................................................................47
3.10.2.2 Name of Each Part and its Function .........................................................................................47
3.10.3 IO Extension Module Master and Slave ..........................................................................................48
3.10.3.1 Functional Specification List .....................................................................................................48
3.10.3.2 Name of Each Part and its Function .........................................................................................48
3.10.4 PG Emulator Module ........................................................................................................................50
3.10.4.1 Functional Specification List .....................................................................................................50
3.10.4.2 Name of Each Part and its Function .........................................................................................50
3.10.5 Pulse I/O Module .............................................................................................................................51
3.10.5.1 Functional Specification List .....................................................................................................51
3.10.5.2 Name of Each Part and its Function .........................................................................................51
CHAPTER 4
4.1
4.2

INSTALLATION ENVIRONMENT .....................................................................................................................52
ATTACHING AND REMOVING UNITS .............................................................................................................52

CHAPTER 5
5.1
5.2
5.3

INSTALLATION AND GROUNDING ...........................................................................................52

MAINTENANCE AND INSPECTION ...........................................................................................53

DAILY INSPECTION .....................................................................................................................................53
PERIODIC INSPECTION ...............................................................................................................................53
BATTERY REPLACEMENT............................................................................................................................53

7

Page 8/ 54 Symbol
Sym
QG18720
Numberbol

Chapter 1
1.1

Model List

1.1.1

HardwareFunction

OutlineName

Outline specification

Standard CPU module

SHPC-111-Z

 Basic instruction: 100 ns
 Program memory: 640 KB
 Number of I/O control points:
Maximum 8,192 points

Baseboard

SHPC-011-Z
SHPC-012-Z
SHPC-013-Z

Power supply module

SHPC-612-Z

SHPC-231-Z
SHPC-233-Z
Digital input module
SHPC-235-Z
SHPC-253-Z
SHPC-311-Z

SHPC-313-Z
Digital output module
SHPC-315-Z
SHPC-333-Z

Digital I/O mixed
moduleSHPC-411-Z

Accessories
Product name

Quantity––

Number of slots: 9
Number of slots: 5
Number of slots: 3
AC 85-264 V input voltage
Output capacity 48 W

–
–
–

–
–
–

–

–

DC 24 V, sink/source
32 bits, connector typeDC 24 V, sink/source
16 bits, screw terminal typeDC 24 V, sink/source
64 bits, connector typeAC 100 V, 8 points 1 common
16 bits, screw terminal typeTransistor output sink type32 bits, output protection: Fuse,
connector typeTransistor output sink type16 bits, output protection: Fuse,screw terminal typeTransistor output sink type64 bits, output protection: Fuse,
connector typeDC 110 V, AC 240 V, relay output
16 bits, screw terminal type
Input: DC 24 V, sink/source
32 bits, connector typeOutput: Transistor output sink type32 bits, output protection:
Fuse, connector type

–

–

–

–

–

–

–

–

–

–

–

–

–

–

–

–

–

–

8

Page 9/ 54 Symbol
Sym
QG18720
Numberbol
Function

Name

Analog input module

SHPC-531-Z

Analog output module

SHPC-511-Z

PG emulator module

SHPC-172-Z

Pulse output module

SHPC-861-Z

Input 8 channels
Resolution 16 bits
Output 4 channels
Resolution 16 bits
Virtual incremental encoder output
A phase, B phase, Z phase2 channels

SHPC-032-Z

Master module

IO extension module

Communication
moduleSHPC-033-Z
Versatilecommunications
moduleOPCN-1
communication
moduleSHPC-161-Z

SHPC-193-Z

Outline specification

Slave module(Maximum 16 slave modules per
master)Versatile communications RS232C
1CH
Versatile communications RS422
2CH
RS485
OPCN-1 compliant

9

Accessories
Product name

Quantity

–

–

–

–

–

–

–
SHPC-021-Z(termination resistor)

–
1

–

–

–

–

Short pin for
termination resistor
connection,
termination resistor

1 eachPage 10/ 54 Symbol
Sym
QG18720
Numberbol

Chapter 2

System Configuration

Company host computer

Factory host computer

Ethernet

Management
computer

FA computerFA
controller

Programmable controller

Ethernet

FA PC

FL-NetProgrammable controller

Generalpurpose PC
Panelcomputer

Sensor

OPCN-1

Display

Remote I/OInverter10

Page 11/ 54 Symbol
Sym
QG18720
Numberbol

Chapter 3
3.1

Specification

General Specifications

Physicalenvironment

Item
Operating ambient
temperature
Storage temperature
Relative temperature
Dust
Corrosion resistanceMechanicaloperatingconditions
Electricaloperatingconditions

Altitude
Antivibration
JIS C9011 compliant
Shock resistance
JIS C9012 compliant
Antinoise
Antistatic discharge
resistance

Structure
Cooling method
Dielectric strength
Insulation resistanceInternal current consumption
WeightSpecifications
0 to 55C-20C to +85C
30 to 95% RH without condensation
No electrically conductive or combustible dust
No corrosive gas
No contact with organic solvents
Elevation of up to 2,000 m
2
Half amplitude: 0.15 mm, fixed acceleration: 9.8 m/s
2 hours in each direction (Total: 2 hours)
2

Peak acceleration: 14.7 m/s
3 times in each direction
AC power supply induced noise Voltage ±1,500 V, rise time 1ns, pulse
width 1 μs
Contact discharge method: ±6 kV, Air discharge method: ±10 kV
Built-in panel type IP3
Natural cooling
As indicated on each module
As indicated on each module
As indicated on each module
As indicated on each module

11Page 12/ 54 Symbol
Sym
QG18720
Numberbol

3.2

Power Supply Module Specifications

3.2.1

Power Supply Specifications
Item

Name
Rated input voltage
Allowable range of voltage
Rated frequency
Allowable range of frequency
Allowable instantaneous
blackout time
Input waveform distortion ratio
Allowable ripple ratio
Leakage current
Inrush current
Rated output capacity
Rated output voltage
Output current
Dielectric strength
Insulation resistanceOverload protection
Overvoltage protection
Operating output
Alarm output
External dimensions (W x D x H)
WeightSpecifications

Remarks

SHPC-612-Z
AC 100/200 V
AC 85 to 264 V
50/60 Hz
47 to 63 Hz
20 ms

At the rated input voltage±5% or less±0.1 V (Vp-p)
0.65 mA or less22.5 A or less
48 W
DC 24 V2A
AC 1,500 V for 1 min
100 MΩ or more (@ DC 500 V)
Drooping characteristic
Protected at 31 V
Yes (On when the CPU performs
operations)
Yes (Off when CPU experiences serious
failure, minor failure, output voltage down)
40 mm x 122 mm x 130 mm
430 g

Between input and ground
Between input and ground

Relay normally open contact(a-contact) output
Relay normally closed contact(b-contact) output*1：Time of turning on the power again
When turning on the power again, wait for more than 1 second after turning off the power.

12

Page 13/ 54 Symbol
Sym
QG18720
Numberbol

3.2.2

Name of Each Part and Its Function(1) Status display
LED(2) Terminal block(8-pole)(1) Status display LED
SymbolPOWER

Display color
Green

Indication
On when the output voltage is within the rated range. Off when
the output voltage is outside the rated range.

(2) Terminal block (8-pole)An M4 x 8-pole terminal block. The allocation of terminals is as follows.
2(Tightening torque: 1.2 N-m, applicable wire size: 2 mm )SymbolINPUT 100-240VAC
LG
FG
RUN
ALM

Specifications
Input
Input
Ground (circuit side)
Ground (frame)
Contact output
Contact output
Contact output
Contact output

Content
AC 85 to 264 V
Power supply filter ground (line ground)
Connected to base module plate (frame ground)
Output during CPU operation. Normally open contact (A-contact)
non-voltage output
Output during serious failure, minor failure, and power supply
failure. Normally closed contact (B-contact)
Non-voltage output

The contacts have a rated voltage of AC 240 V and DC 110 V, and rated current of 1 A.

13

Page 14/ 54 Symbol
Sym
QG18720
Numberbol

3.3

Standard CPU Module Specifications

3.3.1

Performance Specification List
Item

Name
Execution control method
I/O connection method
CPU
Memory type
Programming language
Sequence
instruction
Application
instruction
Program memory capacity
Input and output memory (I/O)
Global memory
Data
Local memory
memory Retain memory
Adverse load information
memoryInstruction execution
time

Number of task units
Number of subprograms

Interface

Operation switch
Service panel
Diagnosis function
Calendar function

BackupNumber of slots occupied
Internal current consumption
External dimensions (W x D x H)
WeightSpecifications
SHPC-111-Z
Stored program method
Cyclic scan method
Directly connected I/O method, remote I/O method32-bit processor
Program memory, data memory
GPC language (data flow form)
0.1 μs to 0.52 μs
0.1 μs to 20 μs
Approximately 1,000 pages (640 KB)
8,192 points
128,000 words
128,000 words
64,000 words
128,000 words
4 (high-speed task, medium-speed task, low-speed task, low-priority
task)
100. However, there is no page restriction on subprograms
RS-422 (dedicated 10-pin square connector)
10BASE-T/100BASE-T
FL-netCompactFlashUSB (mini B connector)
Station numbers for STOP/RUN, RESET, FL-net
LCD (horizontal 36 dots, vertical 24 dots)
LCD operation switches (U/D, L/R, ENT)
CPU hardware check, IO module status check±60 seconds/month (25°C)(Retained for approximately 5 days (25°C) after power stoppage
when the battery is switched off)
Storage of clock and saved memory
Retained for approximately 5 days (25°C) after power stoppage
when the battery is switched off
Guaranteed for 5 years with the battery switched on
Uses both supercapacitor and battery
1 dedicated slot
170 mA
40 mm x 122 mm x 130 mm
360 g

14

Page 15/ 54 Symbol
Sym
QG18720
Numberbol

3.3.2

Name of Each Part and Its Function
Front panel(1) Status display LED

Back(4) LCD(2) Operation switch
RS-422USB

CompactFlash(3) FL-net dedicated station
number setting switch

Commercial products
can be used
Battery switch

10BASE-T/100BASE-TX

FL-net(1) Status display LED
SymbolPWR

Display color
Green

R/L

Green

COM
ALM1
ALM2
LBAT

Green
Red
Yellow
Yellow

ACC

Red

Indication
On when power is supplied to the CPU
R: RUN; On when the CPU performs operations
L: LINK; On when FL-net module link is establishedOn during 100BaseTX/10BaseT communication
On when CPU experiences serious failure
On when CPU experiences minor failure
On when the voltage of the built-in battery is low (only when the CPU is turned on)
On when the CompactFlash card is accessed. (When on, do not remove theCompactFlash card.)(2) Operation switch
SymbolRESETRUN STOP
ENT
U/D
R/L

Content
System reset switch. Note: Only enabled when (RUN STOP) is STOP
RUN (CPU operation execution switch) STOP (CPU operation stop)
When pressed displays the local module IP address. For writing to the CompactFlash card
For writing to the CompactFlash card
UnusedBattery switch
SymbolBAT SWON OFF

Content
Off switch for the backup battery. Unless switched on, backup from the battery is not enabled.
Backup from the supercapacitor is enabled even when switched off. Turn off when keeping
spares for a long time.

(3) FL-net dedicated station number setting switch
Standard IP address: Set 1 to 254 of 192.168.250.1 to 254 with a hexadecimal (01 to FE).The IP address
192.168.250 can be changed with TDFlowEditor.

15

Page 16/ 54 Symbol
Sym
QG18720
Numberbol(4) LCD
StatusSeriousMinor
failurefailureOperation
Operation
stoppedcontinued

Display

Name

CPU
RUN!

CPU RUN

–

–

CPU
STOP!

CPU STOP––

IP address––

IP address

Download
error

Yes

–

SysTsk
TmOver

System task
time over

Yes–

Failed to convert program
code
System task (systemprocess) congestion
occurred.

Task nWDOG

Taskn (1 to
3) watchdog

Yes–

Application task congestion(infinite loop) occurred.

Task n
TmOverTask n (1 to
3) time over–

Yes

Execution of application task
operation cycle was canceled(task omission).

Yes

IO module ID was changed.
The unit number of the relevant
module (0 to F) and slot
number (1 to 9) goes in X.

Yes

Reading IO module ID failed.
(Present bit: 15-bit on → off)
The unit number of the relevant
module (0 to F) and slot
number (1 to 9) goes in X.

Yes

Reading IO module ID failed.
(Error bit: 14-bit off → on)
The unit number of the relevant
module (0 to F) and slot
number (1 to 9) goes in X.

Yes

An IO slot read-write
instruction was executed inrelation to vacant slots.
The unit number of the relevant
module (0 to F) and slot
number (1 to 9) goes in X.

XXX.XXX.
XXX.XXX
DnLoadError

IO ID
ErUXSXIO DefErUXSX

IOFaltErUXSXBusAccErUXSX

IO ID error

IO defineerror

IO faulterror

Bus access
error

–

–

–

–

Content

The CPU started operation.
(Displayed for approximately
1 second)
The CPU stopped operation.
(Displayed for approximately
1 second)

16

Action–––
Revise the program or
download it again.
Revise the program thatcaused congestion.
Revise the program(task n) that caused
congestion.
Revise the program(task n) that caused
congestion.
IO module malfunction,or the extension cable
may be disconnected.
Perform inspection or
replacement.
Likely due to a
non-existent IO module,
dropped connection,
watchdog error, blown
fuse, etc. Perform
inspection or
replacement.
Likely due to an IO
module malfunction,
incomplete initialization,
no external power
supply, etc. Perform
inspection or
replacement.
Revise the program thatcaused the bus accesserror.

Page 17/ 54 Symbol
Sym
QG18720
Numberbol

SysdefErUXSX

Systemdefinition
error

–

Yes

Battery
Low!

Battery low–

Yes

IO allocation and module
mounting status do notmatch.
The unit number of the relevant
module (0 to F) and slot
number (1 to 9) goes in X.
Indicates that the battery built
into the CPU is low.

Revise the IO allocation.

Replace the battery.

(5)RUN STOP switch operation
Switch status
RUN
STOP

TDFlowEditor STOP request
Transition to STOP status
No status change

TDFlowEditor RUN request
In the STOP status, transition to RUN status
No status change

Note: Operation from SHPC-111 Ver 1.06.You can check the version from the type information in the

TDFlowEditor online PLC RAS information.

17

Page 18/ 54 Symbol
Sym
QG18720
Numberbol

3.3.3

CompactFlash Card Operation

With the CPU module CompactFlash you can save and read application programs and write files (FWRITE
function) and read them (FREAD function) from application programs.

3.3.3.1 Operation from the CPU Module
Press the “ENT” button for 3 seconds or more to enter the CompactFlash card operation mode.
D lever
080227101010CF CPU
U or D?

Press ENT
Displaying button for 3 stime

U leverCPU  CFCPU  CFENT OK Write to
Write!
CompactFlashwith ENT
CF  CPU button
CPU  CFENT OK
Read!
Read from
CompactFlashwith ENT
buttonReset applies
the read data.

PleaseReset!

When reading and writing to the CompactFlash Card, the ACC LED comes on. When the LED is on, do notremove the CompactFlash card.

3.3.3.2 Saving to CompactFlash Card
The folder for saving applications is stored in the “CPURUN” folder in the CompactFlash card.

The detailed content is in the following files.
(1)

XXXXXXXX.BIN
Application program (ladder content) file.

(2)

SYSDEFXXXX.BIN
System definition information file.

(3)

TASKXX.BIN
Task configuration information file.

(4)

USERXX.BIN
Adverse load information compressed file. (Window message and contact comment compressed file)18

Page 19/ 54 Symbol
Sym
QG18720
Numberbol
3.3.3.3 Errors when Reading and Writing CompactFlash Card
Display
No FilesSysdef NGFile
CFCard Error
Proces Error
CFCard InitEr

Content
When reading the CompactFlash card, the IO allocation file for the system definition
information file was absent.
When reading the CompactFlash card, the IO allocation file for the system definition
information file did not match the actual configuration.
Failed to write to the CompactFlash card. The CompactFlash card may be invalid.
Failed to read from the CompactFlash card. The CompactFlash card may be invalid.
Failed to initialize CompactFlash card (folder created, old file deleted).The CompactFlash card
may be invalid.

3.3.3.4 CF card recommendation model
The maker model of the CF card which confirmed movement is as follows.

Company
Haiwara Sys-Com Co. Ltd.

Type

Capacity

HPC-CF1GZ3U5

1GB

19

Page 20/ 54 Symbol
Sym
QG18720
Numberbol

3.4

Baseboard Specifications

3.4.1

Performance Specification List
Item

Name
Number of slots
External dimensions (W x D
x H)
Mounting dimensions
WeightSHPC-011-Z
9 slots
482 mm x 149 mm x 130mm
465 mm x 121 mm
1,050 gSpecifications
SHPC-012-Z
5 slots
322 mm x 149 mm x 130mm
305 mm x 121 mm
700 g

SHPC-013-Z
3 slots
242 mm x 149 mm x 130mm
225 mm x 121 mm
520 g

SHPC-011-Z
482 mm

121 mm
149 mm

465 mmSHPC-012-Z
322 mm

121 mm
149 mm

305 mmSHPC-013-Z
242 mm

121 mm
149 mm

225 mm20

Page 21/ 54 Symbol
Sym
QG18720
Numberbol

3.5

Individual Specifications of the Digital Input Module

3.5.1

DC 24 V Input 16 Points

3.5.1.1 Performance Specification List
Item
Name
Number of input points (common configuration)
Input signal
Rated voltage
conditions
Maximum allowable voltage
Allowable ripple ratio

Input circuit
characteristics

Input format

Sink/source shared

Rated current

7 mA (at DC 24 V)

Input impedance

3.3 KΩ

Standard
operatingrange
Input delaytime

Connection

Specifications
SHPC-233-Z
16 points (8 points / common 2 circuits)
DC 24 VDC 30 V
5% or lessOff  On

15 to 30 V

On  Off

0 to 5 V

Off  On

The soft filter times can be changed all at once in theparameter settings.
1 ms, 5 ms, 10 ms, 20 ms, and 70 ms can be set.
DC Type 1
Removable terminal block M3 screw 20-pole
AWG #22 to 18
LED on when each point turns on Logic side
IO CNT: LED on when communication with the CPU moduleis established
Photocoupler insulation
AC 1,500 V 1 minuteBetween the input terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG

On  Off

Input type
External connection
Applicable wire size

Status display LED
Insulation method
Dielectric strength
Insulation resistance

(%)
100

DC26.4V

90
80

DC28.8V70

ON
ON 率 60
rate

Dilating conditions

50
40
30
20

10
0

10

20

30

40

50 55

℃

周囲温度
Ambient
temperature

Dilating conditions
External supply voltage
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightSimultaneously on ratio Maximum 70% (at DC 24 V/55°C)
DC 24 V: For signals
DC 24 V ±10% 35 mA or less (when all points are on)
1 word40 mm x 122 mm x 130 mm
230 g

21

Page 22/ 54 Symbol
Sym
QG18720
Numberbol
3.5.1.2 Name of Each Part and Its Function
Status display LED

Removable terminal block M3 x 20-pole

3.5.1.3 External Connection
Signal
信号名称name

１
3
5
7
8
10

＋

12
＋

14
C1
NC

2
4
6
8
10
12
14
16
18

1

0

3

2

5

4

7

6

9

C0

11

9

13

11

15

13

17

15

19

20

Terminal端子名称
name

3.5.1.4 Internal Circuit
0,8

7,15

C0,C1

22

NC

＋
＋

Page 23/ 54 Symbol
Sym
QG18720
Numberbol

3.5.2

DC 24 V Input 32 Points

3.5.2.1 Performance Specification List
Item
Name
Number of input points (common
configuration)
Rated voltage
Input signal
Maximum allowable voltage
conditions
Allowable ripple ratio
Input format
Rated current
Input impedanceStandard
Off  On
operating
Input circuit
On  Offrange
characteristics
Off  On
Input delaytime
On  Off
Input type
Connection

External connection
Applicable wire size

Status display LED
Insulation method
Dielectric strength
Insulation resistanceSpecifications
SHPC-231-Z
32 points (32 points / common 1 circuit)
DC 24 VDC 30 V
5% or lessSink/source shared
4 mA (at DC 24 V)
5.6 KΩ
15 to 30 V
0 to 5 V
The soft filter times can be changed all at once in theparameter settings.
1 ms, 5 ms, 10 ms, 20 ms, and 70 ms can be set.
DC Type 1
1 40-pole connector (FCN-365P040-AU)
AWG#23 or less (when using a soldered connector)
LED on when each point turns on by flicking switchLogic side
IO CNT: LED on when communication with the CPU moduleis established
Photocoupler insulation
AC 1,500 V 1 minuteBetween the input terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG(%)
100

Dilating conditions

90
80

DC24.0V70

DC26.4VON
ON 率 60rate

DC28.8V

50
40
30
20

10
0

10

20

30

40

50 55

℃

周囲温度
Ambient
temperature

External supply voltage
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightDC 24 V: For signals
DC 24V ±10% 50 mA or less (when all points are on)
2 words
40 mm x 122 mm x 130 mm
220 g

23

Page 24/ 54 Symbol
Sym
QG18720
Numberbol
3.5.2.2 Name of Each Part and Its Function
Status display LED

LED indication changing switch

40-pole connector

3.5.2.3 External Connection
Signal
信号名称 name

A1

A20

B1

B20

＋

0_0

B20

A20

1_0

0_1

B19

A19

1_1

0_2

B18

A18

1_2

0_3

B17

A17

1_3

0_4

B16

A16

1_4

0_5

B15

A15

1_5

0_6

B14

A14

1_6

0_7

B13

A13

1_7

0_8

B12

A12

1_8

0_9

B11

A11

1_9

0_10

B10

A10

1_10

0_11

B9

A9

1_11

0_12

B8

A8

1_12

0_13

B7

A7

1_13

0_14

B6

A6

1_14

0_15

B5

A5

1_15

NC

B4

A4

NC

NC

B3

A3

NC

CO

B2

A2

NC

CO

B1

A1

NC

＋

Connector pin
numberコネクタピン番号

3.5.2.4 Internal Circuit
0.0

1.15

C0

24

Page 25/ 54 Symbol
Sym
QG18720
Numberbol

3.5.3

DC 24 V Input 64 Points

3.5.3.1 Performance Specification List
Item
Name
Number of input points (common configuration)
Rated voltage
Input signal
Maximum allowable voltage
conditions
Allowable ripple ratio

Input circuit
characteristics

Input format

Specifications
SHPC-235-Z
64 points (32 points / common 2 circuits)
DC 24 VDC 30 V
5% or lessSink/source shared

Rated current

4 mA (at DC 24 V)

Input impedance

5.6 KΩ

Standard
operatingrange

15 to 30 V

15 to 30 V

0 to 5 V

0 to 5 V

Off  On

Input typeThe soft filter times can be changed all at once in theparameter settings.
1 ms, 5 ms, 10 ms, 20 ms, and 70 ms can be set.
DC Type 1

External connection

2 40-pole connectors (FCN-365P040-AU)

Applicable wire size

AWG#23 or less (when using a soldered connector)
LED on when each point turns on by flicking switch Logicside
IO CNT: LED on when communication with the CPU
module is established
Photocoupler insulation
AC 1,500 V 1 minuteBetween the input terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG

Input delaytime

Connection

Status display LED
Insulation method
Dielectric strength
Insulation resistanceOn  Off

(%)
100
90
80

DC24.0V70

ON
ON 率 60
rate

Dilating conditions

DC26.4V

50

DC28.8V

40
30
20
10
0

10

20

30

40

50 55

℃

Ambient
temperature
周囲温度

External supply voltage
Internal current consumption
Number of words occupied

DC 24 V: For signals
DC 24 V ±10% 85 mA or less (when all points are on)
4 words

External dimensions (W x D x H)
Weight

40 mm x 122 mm x 130 mm
290 g

25

Page 26/ 54 Symbol
Sym
QG18720
Numberbol
3.5.3.2 Name of Each Part and Its Function
Status display LED

LED indication changing switch

2 40-pole connectors

3.5.3.3 External Connection
Signal nameSignal
信号名称 name

信号名称

2B20 1A1
2A20 1B1

2A1
2B1

1B20
1A20

＋

0_0

1B20

1A20

1_0

2_0

2B20

2A20

3_0

0_1

1B19

1A19

1_1

2_1

2B19

2A19

3_1

0_2

1B18

1A18

1_2

2_2

2B18

2A18

3_2

0_3

1B17

1A17

1_3

2_3

2B17

2A17

3_3

0_4

1B16

1A16

1_4

2_4

2B16

2A16

3_4

0_5

1B15

1A15

1_5

2_5

2B15

2A15

3_5

0_6

1B14

1A14

1_6

2_6

2B14

2A14

3_6

0_7

1B13

1A13

1_7

2_7

2B13

2A13

3_7

0_8

1B12

1A12

1_8

2_8

2B12

2A12

3_8

0_9

1B11

1A11

1_9

2_9

2B11

2A11

3_9

0_10

1B10

1A10

1_10

2_10

2B10

2A10

3_10

0_11

1B9

1A9

1_11

2_11

2B9

2A9

3_11

0_12

1B8

1A8

1_12

2_12

2B8

2A8

3_12

0_13

1B7

1A7

1_13

2_13

2B7

2A7

3_13

0_14

1B6

1A6

1_14

2_14

2B6

2A6

3_14

0_15

1B5

1A5

1_15

2_15

2B5

2A5

3_15

NC

1B4

1A4

NC

NC

2B4

2A4

NC

NC

1B3

1A3

NC

NC

2B3

2A3

NC

CO

1B2

1A2

NC

C1

2B2

2A2

NC

CO

1B1

1A1

NC

C1

2B1

2A1

NC

＋

＋

＋

コネクタピン番号
Connector pin
numberコネクタピン番号
Connector pin
number

3.5.3.4 Internal Circuit

0.0,2.0

1.15,3.15

C0,C1

26

Page 27/ 54 Symbol
Sym
QG18720
Numberbol

3.5.4

AC 100 V Input 16 Points

3.5.4.1 Performance Specification List
Item
Name
Number of input points (common configuration)
Input format
Rated voltage
Maximum allowable voltage
Input signal
Waveform distortion ratio
conditions
Rated frequency
Allowable range of frequency
Inrush current
Rated current
Input impedance
Off  On
Standard
operating range
On  Off
Input circuit
Off  On
characteristics
On  Off
Input delay time
Soft filter

Number of words occupied
External dimensions (W x D x H)

Specifications
SHPC-253-Z
16 points (8 points / common 2 circuits)
DC 24 VAC 100 to 120 V
AC 132 V
5% or less
50/60 Hz
47 to 63 Hz
Maximum 150 mA
10 mA/point (AC 100/120 V)
10 kΩ (50 Hz), 9 kΩ (60 Hz)
80 to 132 V
0 to 20 V
Approximately 10 ms
Approximately 10 ms
The soft filter times can be changed all at once in theparameter settings.
10 ms, 20 ms, and 70 ms can be set.
AC Type 1
Removable terminal block M3 screw 20-pole
AWG #22 to 18
LED on when each point turns on
Logic side
IO CNT: LED on when communication with the CPU
module is established
Photocoupler insulation
AC 1,500 V 1 minuteBetween the input terminals as a group and FG
10 MΩ or more when measured with DC 500 V
insulation resistance tester
Between the input terminals as a group and FG
AC 100 to 120 V: For signals
DC 24 V ±10%40 mA or less (when all points are on)
1 word40 mm x 122 mm x 130 mm

Weight250 g

Connection

Input type
External connection
Applicable wire size

Status display LED
Insulation method
Dielectric strength
Insulation resistance
External supply voltage
Internal current consumption

27

Page 28/ 54 Symbol
Sym
QG18720
Numberbol
Status display LED

3.5.4.2 Name of Each Part and Its Function

Removable terminal block M3 x 20-pole

3.5.4.3 External Connection
Signal
信号名称 name

１
3
5
7
8
10
12
14
C1
NC

2
4
6
8
10
12
14
16
18

1

0

3

2

5

4

7

6

9

C0

11

9

13

11

15

13

17

15

19

NC

20

端子名称
Terminal
name3.5.4.4 Internal Circuit
0,8

7,15

C0,C1

28

Page 29/ 54 Symbol
Sym
QG18720
Numberbol

3.6

Individual Specifications of the Digital Output Module

3.6.1

Transistor Output 16 Points

3.6.1.1 Performance Specification List
Item
Name
Number of output points (common
configuration)
Rated voltage
Output power
conditions
Allowable range of voltage
Output format
Maximum load current
Output voltage drop
Output circuit
characteristics

Output delaytime

Off  OnOn  Off

Leakage current when off
Output type
Withstand surge current
Outputprotection type

Built-in fuse
Surge suppression circuit
Other output protection

Maximum opening/closing speed
Connection

External connection
Applicable wire size

Status display LED

Insulation method
Dielectric strength
Insulation resistance
Dilating conditions
External power supply
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightSpecifications
SHPC-313-Z
16 points (8 points / common 2 circuits)
DC 12 to 26 V
DC 10.2 to 30 V
Sync output
0.6 A/point, 4 A/common
1.5 V or less (at 0.6 A)
1 ms or less
1 ms or lessMaximum 0.1 mATransistor output
2 A 10 ms
125 V 7 A × 2 (Replacement of fuses cannot be performed by
the user)Varistor
None
1,800 times/hour (This is a restriction when there is aninduced load. There is no restriction when there is a
resistance load.)
Removable terminal block M3 screw 20-pole
AWG #22 to 18
LED on when each point turns on
Logic side
IO CNT: LED on when communication with the CPU moduleis establishedEXT:
LED on when connected to external power
FUSE: LED on when the fuse blows or when not connected
to external power
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG
None
DC 24 V: For driving transistors
DC 24V ±10%40 mA or less (when all points are on)
1 word40 mm x 122 mm x 130 mm
230 g

29

Page 30/ 54 Symbol
Sym
QG18720
Numberbol
Status display LED

3.6.1.2 Name of Each Part and Its Function

Removable terminal block M3 x 20-pole

3.6.1.3 External Connection
Signal
信号名称name

１
L

3
L

5
L

7
L

M0

＋

9
L

11
L

13
L

15
L

＋

M1

2
4
6
8
10
12
14
16
18

1

0

3

2

5

4

7

6

9

P0

L

11

8

13

10

15

12

17

14

19

L
L
L

L
L
L
L

P1

20

Terminal端子名称
name

3.6.1.4 Internal Circuit
0,8

7,15

P0,P1
AVR

Fuse

30

M0,M1

Page 31/ 54 Symbol
Sym
QG18720
Numberbol

3.6.2

Transistor Output 32 Points

3.6.2.1 Functional Specification List
Item
Name
Number of output points (common
configuration)
Rated voltage
Output power
conditions
Allowable range of voltage
Output format
Maximum load current
Output circuit
characteristics

Outputprotection typeSpecifications
SHPC-311-Z
32 points (32 points / common 1 circuit)
DC 12 to 26 V
DC 10.2 to 30 V
Sync output
0.12 A/point (DC 30) 3.2 A/common

Output voltage drop

1.5 V or less (at 0.12 A)

Off  OnOn  Off
Leakage current when off
Output type
Withstand surge current

1 ms or less
1 ms or lessMaximum 0.1 mATransistor output
2 A 10 ms
125 V 5 A (Replacement of fuses cannot be performed by theuser)
Zener diodeNone
3,600 times/hour (This is a restriction when there is an induced
load. There is no restriction when there is a resistance load.)

Output delay
time

Built-in fuse
Surge suppression circuit
Other output protection

Maximum opening/closing speed

Connection

External
connection
Applicable wire
size

Status display LED

Insulation method
Dielectric strength
Insulation resistance
Dilating conditions
External power supply
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
Weight

1 40-pole connector (FCN-365P040-AU)
AWG#23 or less (when using a soldered connector)
LED on when each point turns on by flicking switch
Logic side
IO CNT: LED on when communication with the CPU module isestablishedEXT:
LED on when connected to external power
FUSE: LED on when the fuse blows or when not connected toexternal power
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG
None
DC 12 to 24 V, 52 mA: For driving transistors
DC 24 V ±10%45 mA or less (when all points are on)
2 words
40 mm x 122 mm x 130 mm
220 g

31

Page 32/ 54 Symbol
Sym
QG18720
Numberbol
3.6.2.2 Name of Each Part and Its Function
Status display LED

LED indication changing switch

40-pole connector

3.6.2.3 External Connection
信号名称 nameSignal

A1

B1

L

0_0

B20

A20

1_0

L

L

0_1

B19

A19

1_1

L

0_2

B18

A18

1_2

0_3

B17

A17

1_3

0_4

B16

A16

1_4

0_5

B15

A15

1_5

0_6

B14

A14

1_6

0_7

B13

A13

1_7

0_8

B12

A12

1_8

0_9

B11

A11

1_9

0_10

B10

A10

1_10

0_11

B9

A9

1_11

0_12

B8

A8

1_12

0_13

B7

A7

1_13

0_14

B6

A6

1_14

0_15

B5

A5

1_15

NC

B4

A4

NC

NC

B3

A3

NC

Ｐ０

B2

A2

Ｍ０

Ｐ０

B1

A1

Ｍ０

L
L
L
L

A20

B20

L

L
L
L
L

L

＋

Connector pin
numberコネクタピン番号

3.6.2.4 Internal Circuit
0.0

1.15

P0
AVR

Fuse

32

M0

Page 33/ 54 Symbol
Sym
QG18720
Numberbol

3.6.3

Transistor Output 64 Points

3.6.3.1 Functional Specification List
Item
Name
Number of output points (common
configuration)
Output power Rated voltage
conditions
Allowable range of voltage
Output format
Maximum load current
Output voltage drop
Output circuit
characteristics

Output delaytime

Off  OnOn  OffDC 12 to 26 V
DC 10.2 to 30 V
Sync output
0.12 A/point, 3.2 A/common
1.5 V or less (at 0.12 A)
1 ms or less
1 ms or lessMaximum 0.1 mA

Output typeTransistor output

Withstand surge current

0.3 A, 10 ms
125 V 5 A x 2 (Replacement of fuses cannot be performed by theuser)
Zener diodeSurge suppression circuit
Other output protection

Maximum opening/closing speed
Connection

64 points (32 points / common 2 circuits)

Leakage current when off

Built-in fuse
Outputprotection typeSpecifications
SHPC-315-Z

External connection
Applicable wire size

Status display LED

Insulation method
Dielectric strength
Insulation resistance
Dilating conditions
External power supply
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightNone
3,600 times/hour (This is a restriction when there is an induced
load. There is no restriction when there is a resistance load.)
2 40-pole connectors (FCN-365P040-AU)
AWG#23 or less (when using a soldered connector)
LED on when each point turns on by flicking switch
Logic side
IO CNT: LED on when communication with the CPU module isestablishedEXT:
LED on when connected to external power
FUSE: LED on when the fuse blows or when not connected toexternal power
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG
None
DC 12 to 24 V, 80 mA: For driving transistors
DC 24 V ±10%90 mA or less (when all points are on)
4 words
40 mm x 122 mm x 130 mm
290 g

33

Page 34/ 54 Symbol
Sym
QG18720
Numberbol
3.6.3.2 Name of Each Part and Its Function
Status display LED

LED indication changing switch

40-pole connector

3.6.3.3 External Connection
信号名称 nameSignalSignal
信号名称 name

2B20 1A1
2A20 1B1

L

0_0

1B20

1A20

1_0

L

L

2_0

2B20

2A20

3_0

L

L

0_1

1B19

1A19

1_1

L

L

2_1

2B19

2A19

3_1

L

0_2

1B18

1A18

1_2

L

L

2_2

2B18

2A18

3_2

0_3

1B17

1A17

1_3

L

L

2_3

2B17

2A17

3_3

0_4

1B16

1A16

1_4

L

L

2_4

2B16

2A16

3_4

0_5

1B15

1A15

1_5

L

L

2_5

2B15

2A15

3_5

0_6

1B14

1A14

1_6

2_6

2B14

2A14

3_6

0_7

1B13

1A13

1_7

2_7

2B13

2A13

3_7

0_8

1B12

1A12

1_8

2_8

2B12

2A12

3_8

0_9

1B11

1A11

1_9

2_9

2B11

2A11

3_9

0_10

1B10

1A10

1_10

2_10

2B10

2A10

3_10

0_11

1B9

1A9

1_11

2_11

2B9

2A9

3_11

0_12

1B8

1A8

1_12

2_12

2B8

2A8

3_12

0_13

1B7

1A7

1_13

2_13

2B7

2A7

3_13

0_14

1B6

1A6

1_14

2_14

2B6

2A6

3_14

0_15

1B5

1A5

1_15

2_15

2B5

2A5

3_15

NC

1B4

1A4

NC

NC

2B4

2A4

NC

NC

1B3

1A3

NC

NC

2B3

2A3

NC

Ｐ０

1B2

1A2

Ｍ０

Ｐ1

2B2

2A2

Ｍ1

Ｐ０

1B1

1A1

Ｍ０

Ｐ1

2B1

2A1

Ｍ1

L
L
L
L

2A1
2B1

1B20
1A20
L

L

L

＋

Connector pin
numberコネクタピン番号

Connector pin
numberコネクタピン番号

3.6.3.4 Internal Circuit
0.0,2.0

1.15,3.15

P0,P1
AVR

Fuse

34

M0,M1

L
L
L
L

L

＋

Page 35/ 54 Symbol
Sym
QG18720
Numberbol

3.6.4

Relay Output 16 Points

3.6.4.1 Functional Specification List
Item
Model
Number of output points (common
configuration)
Rated voltage
Allowable range of voltage
Output power
Rated frequency
conditions
Allowable range of
frequency
Output format
Maximum load current
Output circuit
characteristics

Minimum switchingvoltage/current
Off  On
Output delaytime
On  Off
Leakage current when off

Built-in fuse
Output typeOutputprotection type Surge suppression circuit
Other output protection
Maximum opening/closing speed
External connection
Connection
Applicable wire size
Status display LED
Insulation method
Dielectric strength
Insulation resistance
Dilating conditions
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightSpecifications
SHPC-333-Z
16 points (8 points / common 2 circuits)
AC 240 V, DC 110 V
AC 264 V or less, DC 140 V or less––
Relay output
DC 30 V/AC 264 V: 2.2 A/point, 8 A/common
DC 110 V: 0.2 A/point, 1.6 A/common
DC 5 V
Approximately 10 ms
Approximately 10 ms
Maximum 0.1 mA
None
Relay (both AC and DC)
Varistor
None
1,800 times/hour
Removable terminal block M3 screw 20-pole
AWG #22 to 18
LED on when each point turns on
Logic side
IO CNT: LED on when communication with the CPU module isestablished
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG
None
DC 24 V ±10%145 mA or less (when all points are on)
1 word40 mm x 122 mm x 130 mm
300 g

35

Page 36/ 54 Symbol
Sym
QG18720
Numberbol
3.6.4.2 Name of Each Part and Its Function

Status display LED

Removable terminal block M3 x 20-pole

3.6.4.3 External Connection
Signal name
信号名称

１
L

3
L

5
L

7
L

8
L

10
L

＋

12
＋

L

14
L

C1
NC

2
4
6
8
10
12
14
16
18

1

0

3

2

5

4

7

6

L

9

C0

11

9

13

11

15

13

17

15

19

L

＋

L
L

＋

L
L
L
L

NC

20

Terminal端子名称
name

3.6.4.4 Internal Circuit

0,8

Ｒ

7,15
Ｒ

C0,C1

36

Page 37/ 54 Symbol
Sym
QG18720
Numberbol

3.7

Individual Specifications of the Digital I/O Mixed Module

3.7.1

DC 24 V Input 32 Points, Output 32 Points

3.7.1.1 Performance Specification List
Item
Name
Number of input points (common configuration)
Rated voltage
Input signal
Maximum allowable voltage
conditions
Allowable ripple ratio
Input format
Rated current
Input impedance
15 to 30 V
Standard
Input circuit
operating range
0 to 5 V
characteristics
Off  On
Input delay timeOn  Off
Input type
Number of output points (common configuration)
Rated voltage
Output power
conditions
Allowable range of voltage
Output format
Maximum load current
Output voltage dropOff  On
Output circuit
Output delay
characteristicstime
On  Off
Leakage current when off
Output type
Withstand surge current
Outputprotection type

Built-in fuse
Surge suppression circuit
Other output protection

Maximum opening/closing speed
Connection

External connection
Applicable wire size

Status display LED

Insulation method
Dielectric strength
Insulation resistance

Dilating conditions
External supply voltage

Specifications
SHPC-411-Z
32 points (32 points / common 1 circuit)
DC 24 VDC 30 V
5% or lessSink/source shared
4 mA (at DC 24 V)
5.6 KΩ
15 to 30 V
0 to 5 V
The soft filter times can be changed all at once in theparameter settings.
1 ms, 5 ms, 10 ms, 20 ms, and 70 ms can be set.
DC Type 1
32 points (32 points / common 1 circuit)
DC 12 to 26 V
DC 10.2 to 30 V
Sync output
0.12 A/point (DC 30) 3.2 A/common
1.5 V or less (at 0.12 A)
1 ms or less
1 ms or lessMaximum 0.1 mATransistor output
2 A 10 ms
125 V 5 A (Replacement of fuses cannot be performed by
the user)
Zener diodeNone
3,600 times/hour (This is a restriction when there is an induced
load. There is no restriction when there is a resistance load.)
2 40-pole connectors (FCN-365P040-AU)
AWG#23 or less (when using a soldered connector)
LED on when each point turns on by flicking switch
Logic side
IO CNT: LED on when communication with the CPU
module is establishedEXT:
LED on when connected to external power
FUSE:
LED on when the fuse blows or when notconnected to external power
Photocoupler insulation
AC 1,500 V 1 minuteBetween the input terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation
resistance tester
Between the input terminals as a group and FG
Simultaneously on ratio
Maximum 70% (at DC 24 V/55°C)
DC 24 V: For signals
37

Page 38/ 54 Symbol
Sym
QG18720
Numberbol
Item
External power supply
Internal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightSpecifications
DC 12 to 24 V, 52 mA: For driving transistors
DC 24 V ±10% 90 mA or less (when all points are on)
4 words
40 mm x 122 mm x 130 mm
290 g

38

Page 39/ 54 Symbol
Sym
QG18720
Numberbol
3.7.1.2 Name of Each Part and Its Function
Status display LED

LED indication changing switch

40-pole connector

3.7.1.3 External Connection

Signal
信号名称 name

2B20 1A1
2A20 1B1

2A1
2B1

Signal
信号名称 name

L

0_0

1B20

1A20

1_0

L

2_0

2B20

2A20

3_0

L

0_1

1B19

1A19

1_1

L

2_1

2B19

2A19

3_1

L

0_2

1B18

1A18

1_2

L

2_2

2B18

2A18

3_2

L

0_3

1B17

1A17

1_3

L

2_3

2B17

2A17

3_3

L

0_4

1B16

1A16

1_4

L

2_4

2B16

2A16

3_4

L

0_5

1B15

1A15

1_5

L

2_5

2B15

2A15

3_5

0_6

1B14

1A14

1_6

2_6

2B14

2A14

3_6

0_7

1B13

1A13

1_7

2_7

2B13

2A13

3_7

0_8

1B12

1A12

1_8

2_8

2B12

2A12

3_8

0_9

1B11

1A11

1_9

2_9

2B11

2A11

3_9

0_10

1B10

1A10

1_10

2_10

2B10

2A10

3_10

0_11

1B9

1A9

1_11

2_11

2B9

2A9

3_11

0_12

1B8

1A8

1_12

2_12

2B8

2A8

3_12

0_13

1B7

1A7

1_13

2_13

2B7

2A7

3_13

0_14

1B6

1A6

1_14

2_14

2B6

2A6

3_14

0_15

1B5

1A5

1_15

2_15

2B5

2A5

3_15

NC

1B4

1A4

NC

NC

2B4

2A4

NC

NC

1B3

1A3

NC

NC

2B3

2A3

NC

Ｐ０

1B2

1A2

Ｍ０

CO

2B2

2A2

NC

Ｐ０

1B1

1A1

Ｍ０

CO

2B1

2A1

NC

1B20
1A20
L

L

＋

＋

＋

コネクタピン番号
Connector pin
numberコネクタピン番号
Connector pin
number

3.7.1.4 Internal Circuit

0.0
2.0

3.15

1.15
C0

P0
AVR

Fuse

M0

39

Page 40/ 54 Symbol
Sym
QG18720
Numberbol

3.8

Analog Input: 8 Channels

3.8.1

Functional Specification List

Item
Name

Specifications
SHPC-531-Z

Input register
Number of input channels
Input impedance
Resolution
System accuracy (in relation toscale)
Digital output value
A/D conversion time
External
connection
Connection
Applicable wire
size
Status display LED
Insulation method
Dielectric strength
Insulation resistanceInternal current consumption
Number of words occupied
External dimensions (W x D x
H)
Weight

3.8.2

0 to +5 V, 0 to +10 V, +1 to +5 V, -5 to +5 V, -10 to+10 V
0 to +10 v, -5 to +5 v, -10 to +10 v
Current (4 ch) 0 to +20 mA, +4 to 20 mA
8 channels (of which current can be input in 4)
Voltage input: 1 MΩ, Current input: 250 Ω
16 bits
12 bits
Voltage (8 ch)

16 bits
12 bits
16 bits±0.1% or less (25°C), ±1.0% or less (0 to 55°C)-32768 to +32768
0.5 ms/8 ch
Removable terminal block M3 screw 20-pole
AWG #22 to 18
RUN: On when normal, ERR: On when abnormal
IO CNT: LED on when communication with the CPU module is established
Photocoupler insulation. However, uninsulated between channels
AC 1,500 V 1 minuteBetween the input terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
DC 24 V ±10%100 mA or less
8 words
40 mm x 122 mm x 130 mm
250 g

Name of Each Part and Its Function
Status display LED

Removable terminal block M3 x 20-pole

40

Page 41/ 54 Symbol
Sym
QG18720
Numberbol

3.8.3

External Connection
1: Voltage input 0 (VIN0)
2: Voltage input 1 (VIN1)
3: Current input 0 (IIN0)
4: Current input 1 (IIN1)
5: GND0
6: GND1
7: Voltage input 2 (VIN2)
8: Voltage input 3 (VIN3)
9: Current input 2 (IIN2)
10: Current input 3 (IIN3)
11: GND2
12: GND3
13: Voltage input 4 (VIN4)
14: Voltage input 5 (VIN5)
15: GND4
16: GND5
17: Voltage input 6 (VIN6)
18: Voltage input 7 (VIN7)
19: GND6
20: GND7

Voltage input connection
Signal name
VIN1
IIN1
GN
D

GND
1
VIN3

FG

IIN3
GN
D
GN
D

GN
D0
VIN
2
IIN2

7
8
9
10

GND
20
7

GN
D

IIN0

5
6

GND 16
5
VIN7 18

FG

VIN0

3
4

GND 12
3
VIN5 14

FG

1
2

11
13
15
17
19

GN
D2
VIN
4
GN
D4
VIN
6
GN
D6

FG

GN
D

FG

GN
D

FG

GN
D
GN
D

FG

FG

Terminal nameCurrent input connection
Signal name
VIN1
IIN1
GN
D

GND
1
VIN3

FG

IIN3

GN
D

FG

1

VIN0

3

IIN0

5

GN
D0
VIN
2
IIN2

2
4
6
7
8
9
10

GND 12
3
VIN5 14
GND 16
5
VIN7 18
GND
20
7

11
13
15
17
19

Terminal name

41

GN
D2
VIN
4
GN
D4
VIN
6
GN
D6

FG

FG

GN
D

GN
D

Page 42/ 54 Symbol
Sym
QG18720
Numberbol

3.8.4

Scaling

The relationship between the input data and digital conversion value is as follows.
0 to +5 V (0 to 20 mA)

0 to +10 V
FFFh FFFFh

FFFFh(65535)

Digital conversion value

Digital conversion value(4095) (65535)

0000

0V

16bit

+5V

(0mA)

Analog value(+20mA)

000

0000

12bit

16bit

0V

+10V
Analog value+1 to +5 V (+4 to +20 mA)

Digital conversion valueFFFFh(65535)

0000
0
16bit

+1V
(+4mA)

Analog value+5V(+20mA)-5 to +5 V
7FFFh

7FFh

000

Digital conversion value(2047) (32767)(2047) (32767)

0000

000

F800h 8000h(-2048)(-32768)
12bit

7FFFh

Digital conversion value

7FFh-10 to +10 V

F800h
-5V

Analog0V
value

0000

8000h

(-2048)(-32768)

+5V

16bit

12bit

42

16bit

-10V

0V
Analog value+10VPage 43/ 54 Symbol
Sym
QG18720
Numberbol

3.9

Analog Output: 4 Channels

3.9.1

Functional Specification List

Item
Name

Specifications
SHPC-511-Z

Output register
Number of output channels
External load resistance
Resolution
System accuracy (in relation toscale)
Digital input value
D/A conversion time
External
connection
Connection
Applicable wire
size
Status display LED
Insulation method
Dielectric strength
Insulation resistanceInternal current consumption
Number of words occupied
External dimensions (W x D x
H)
Weight3.9.2

Voltage (4 ch)

0 to +5 V, 0 to +10 V, +1 to +5 V, -5 to +5 V, -10 to+10 V
0 to +10 v, -5 to +5 v, -10 to +10 v
0 to +20 mA, +4 to 20 mA

Current (4 ch)
4 channels
Voltage output: 1 kΩ or more, current output: 500 Ω or less16 bits
12 bits

16 bits
12 bits
16 bits±0.1% or less (25°C), ±1.0% or less (0 to 55°C)-32768 to +32768
0.5 ms/4 ch
Removable terminal block M3 screw 20-pole
AWG #22 to 18
ERR: On when abnormal
IO CNT: LED on when communication with the CPU module is established
Photocoupler insulation. However, uninsulated between channels
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
DC 24 V ±10%120 mA or less
4 words
40 mm x 122 mm x 130 mm
250 g

Name of Each Part and Its Function

Status display LED

Removable terminal block M3 x 20-pole

43Page 44/ 54 Symbol
Sym
QG18720
Numberbol

3.9.3

External Connection
1: VICI1
2: Current output 1 (I1)
3: Voltage output 1(V1)
5: VICI2

4: COM
6: Current output 2 (I2)

7: Voltage output 2(V2)
9: VICI3

8: COM
10: Current output 3(I3)
12: COM

11: Voltage output 3(V3)
13: VICI4

14: Current output 4(I4)
16: COM

15: Voltage output 4(V4)
17: FG

18: FG
19: FG
20: FG

Voltage output connection
Signal name

A

I1

B

COM

A

I2

B

COM
I3

A

I4

A

FG
FG

A: Control valve etc.
B: 1 kΩ or more external load resistance

3

V1

5

VICI2

7

V2

9

VICI3

11

V3

13

VICI4

15

V4

17

FG

19

FG

1

VICI1

3

V1

5

VICI2

7

V2

9

VICI3

11

V3

13

VICI4

15

V4

17

FG

19

FG

6
8
10

14

COM 16

B

VICI1

4

COM 12

B

1
2

18
20

Terminal nameCurrent output connection
Signal name
I1

A

B

COM
I2

A

B

COM
I3

A

4
6
8
10

COM 12

B

I4

A

2

14

COM 16

B

FG
FG

Terminal name
A: Control valve etc.
B: 500 kΩ or less external load resistance

44

18
20

Page 45/ 54 Symbol
Sym
QG18720
Numberbol

3.9.4

Scaling

The relationship between the input data and output signal is as follows.
0 to +5 V (0 to +20 mA)

0 to +10 V

Analog output value+10V

Analog output value+5V(+20mA)

16bit 00000

0Digital input value

16bit

FFFFh (65535)

12bit

0000
000

FFFFh (65535)
Digital input value FFFh (4095)+1 to +5 V (+4 to +20 mA)

Analog output value+5V(+20mA)+1V(+4mA)

16bit

0
0000

FFFFh (65535)
Digital input value

+5V

+10V

Analog output value-10 to +10 V

Analog output value-5 to +5 V

0V

-5V
16bit

0000

0V

-10V

Digital input value
8000h (32768) FFFFh (65535)

16bit

0000

Digital input value
8000 (32768)

FFFFh (65535)

16bit+- 8000h (-32768)

0 (0)7FFFh (32767)

16bit+- 8000h (-32768)

0 (0)7FFFh (32767)

12bit

0 (0)

7FFh

12bit

0 (0)

7FFh (2047)

F800h (-2048)(2047)

45

F800h (-2048)

Page 46/ 54 Symbol
Sym
QG18720
Numberbol

3.10 Communication Module Individual Specifications
3.10.1 Versatile Communications Module
3.10.1.1 Functional Specification List
Item
Name
Transmission channel
Internal standard protocol
Transmission method
Synchronization method
Transmission rate
Transmission distance
Number of units that canbe connected
Connector
Insulation method
Dielectric strength
Insulation resistanceInternal current
consumption
Number of bytes occupied
Maximum mountable number
External dimensions(W x D x H)
WeightSpecifications
SHPC-161-Z
RS-232C 1 channel
RS-422 2 channels
Fuji Electric: POD UG series Toyo Denki μGPCsx protocol compliant
Touch
panel
Komatsu: AIP KDP series Toyo Denki μ-GPCH protocol compliant
Full duplex (with communication protocol)
Asynchronous
1,200/2,400/4,800/9,600/19,200/38,400/57,600 bps
Within 15 m
Within 1 km
1: 1 (1 external device)
D-sub 9-pin connector (male) millimeter
D-sub 9-pin connector (female) inch
screw
screw
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
DC 24 V ±10%100 mA or less
8 words
8
40 mm x 122 mm x 130 mm
260 g
Status display LED

3.10.1.2 Name of Each Part and Its Function

D-sub connector

External connection
CH1

CH2

CH3

46

Page 47/ 54 Symbol
Sym
QG18720
Numberbol

3.10.2 OPCN-1 Master Module
3.10.2.1 Functional Specification List
Item
Name
Transmission channel
Transmission method
Synchronization method
Transmission rate
Transmission distance
Number of units that can beconnected
External
connection
Connection
Applicable wire
size
Insulation method
Dielectric strength
Insulation resistanceInternal current consumption
Number of words occupied
Maximum mountable number
External dimensions (W x D x H)
WeightSpecifications
SHPC-193-Z
RS-485 1 channel
Half duplex
Bit timing
125 k/250 k/500 k/1 M/ (2 M) bps
125 kbps (1000 m), 250 kbps (800 m), 500 kbps (480 m), 1 Mbps (240 m)
1: 31
Terminal block M3 screw 20-pole
AWG #22 to 18
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
DC 24 V ±10%100 mA or less
8,192 words
8
40 mm x 122 mm x 130 mm
250 g

3.10.2.2 Name of Each Part and Its Function

Status display LED
Setting switch

Terminal block M3 x 5-pole

47

Page 48/ 54 Symbol
Sym
QG18720
Numberbol

3.10.3 IO Extension Module Master and Slave
3.10.3.1 Functional Specification List
Item
Name
Number of units thatcan be connected
Installation position

MasterSlave
MasterSlave
MasterSlave

Connection method
Signal level
MasterStatus display LED
Slave
Dielectric strength
Insulation resistance
MasterSlave
External dimensions (W x D x H)
Master
WeightSlave
Internal current
consumption

Specifications
SHPC-032-Z
SHPC-033-Z
1
16 slave modules can be connected per master
Install in unit with CPU. (1 base 1 unit only)
Install in CPU slot position of unit with no CPU.
Dedicated extension cable (0.3 m, 0.6 m, 1 m, 2 m, 5 m, 10 m), SX bus total
length max 10 m
RS485
IO CNT: LED on when communication with the CPU module is established
RUN:
LED on when the local CPU is operating normallyERR:
LED on when the local CPU WDT time up occurs
0 to F: LED on when the relevant unit is in RS485 communication
IO CNT: LED on when communication with the CPU module is established
RUN:
LED on when the local CPU is operating normallyERR:
LED on when the local CPU WDT time up occurs
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
38 mA
56 mA
40 mm x 122 mm x 130 mm
220 g
270 g

3.10.3.2 Name of Each Part and Its Function
Status display LED

Status display LED

Setting switch
Connector
Connector

SHPC-032-Z
Master module

SHPC-033-Z
Slave module

Note: Caution when disconnecting the extension cable
Even if the extension cable is disconnected, the CPU experiences only a minor failure (normal operation
continues when there is a system definition conflict or when IO is not implemented and not set) but continues
operation. To stop output when IO drops, access the announce relay and create an application program.
48

Page 49/ 54 Symbol
Sym
QG18720
Numberbol
Connection method

SHPC-032 master module

SHPC-033 slave module

ADDR 0ADDR 1
Dedicated extension cable CA-SHEX003 (0.3 m)
 CA-SHEX006 (0.6 m)
 CA-SHEX010 (1 m)
 CA-SHEX020 (2 m) CA-SHEX050 (5 m) CA-SHEX100 (10 m)

ADDR 2ADDR 3ADDR 4

Termination resistor
built-in connector
SHPC-021-Z

49

Page 50/ 54 Symbol
Sym
QG18720
Numberbol

3.10.4 PG Emulator Module
3.10.4.1 Functional Specification List
Item
Name
Pulse generation method
Reference clock frequency
Setting resolution
Number of output pulses
Output frequency
Output frequency resolution
Periodic error
Waveform ratio
Phase difference
Signal level
Connector
Insulation method
Dielectric strength
Insulation resistanceInternal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightSpecifications
SHPC-172-Z
Addition method
67.108860 kHz
20 bits
100 to 65,535 pulses/1 rotation
0 to 624,000 Hz
1.0 HzT ±0.01 T (0 to 624 Hz)
0.5 T ±0.05 T (0 to 624 Hz)
0.25 T ±0.05 T (0 to 624 Hz)
RS-422 A phase, B phase, Z phase
D-sub 9-pin connector (female)
Photocoupler insulation
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
DC 24 V ±10%100 mA or less
8 words
40 mm x 122 mm x 130 mm
230 g

3.10.4.2 Name of Each Part and Its Function

Status display LED

Connector
FemaleExternal connection50

Page 51/ 54 Symbol
Sym
QG18720
Numberbol

3.10.5 Pulse I/O Module
3.10.5.1 Functional Specification List
Item
Name
Input method
Maximum input
frequency
Frequency
input
up-downcounter

Resolution
Insulation method
Frequency
detection accuracy
Connector
Output method

Frequency
outputMaximum output
frequency
Resolution
Insulation method
Pulse output
accuracy
Connector

Dielectric strength
Insulation resistanceInternal current consumption
Number of words occupied
External dimensions (W x D x H)
WeightSpecifications
SHPC-861-Z
DC 5, 12, 15, 24 V input 2 phase, single phase
100 kHz4 W occupied per 1 ch
(Frequency detection 2 W, input up-down counter 2 W)
Photocoupler insulation±0.01% or lessD-sub 9-pin connector (male)DC 24 V external input
Single phase
32.767 kHz
1 W occupied per 1 ch
Photocoupler insulation±0.01% or lessD-sub 9-pin connector (female)
AC 1,500 V 1 minuteBetween the output terminals as a group and FG
10 MΩ or more when measured with DC 500 V insulation resistance tester
Between the input terminals as a group and FG
DC 24 V ±10%100 mA or less
Input 8 W, output 8 W
40 mm x 122 mm x 130 mm
230 g

3.10.5.2 Name of Each Part and Its Function
Status display LED

Connector

51

Page 52/ 54 Symbol
Sym
QG18720
Numberbol

Chapter 4
4.1

Installation and Grounding

Installation Environment

The following environmental conditions should be avoided when installing the μGPCsH system.
(1)

Locations with ambient temperature outside the range of 0 to 55°C

(2)

Locations with ambient humidity outside the range of 30 to 95％(3)

Locations where condensation occurs due to rapid temperature change(4)

Locations where combustible or corrosive gas is present(5)Locations subject to strong impacts or vibration(6)

Locations subject to strong electric fields or magnetic fields(7)

Locations where conductive powder such as dust or iron powder and organic solvents are present in large
quantities(8)

Locations subject to rainfall or direct sun light

4.2

Attaching and Removing Units

This section explains how to attach the power supply module, CPU module, I/O module, etc., to the baseboard
and to remove them.
(1)

Attaching a unit

1.

Attach the socket on the bottom of the unit to the hook below the slot on the baseboard and insert the top of
the module.

2.

Check that the baseboard and module connectors are connected.

3.

Tighten the attachment screws at the top of the module.

(2)

Removing a unit

1.

Loosen theattachment screws at
the top of the module.

2.

Pivot the module
towards you on its
hook and lift it off.

Base unit
Base unit

Unit
Unit
Attachment hook

Attachment hook52

Page 53/ 54 Symbol
Sym
QG18720
Numberbol

Chapter 5

Maintenance and Inspection

In order to use the μGPCsH correctly at all times, it is necessary to carry out the following daily and periodic
inspections.

5.1

Daily Inspection

Item
The attachment of allparts
The connection of allparts
Check the power
supply module LEDs.
Check the CPU
module LED.
Check the extension
module LEDs.

Check the I/O module
LEDs.

5.2

Content
 Check that attachment screws are not loose.

Procedure Tightening Check that terminal screws are not loose.

 Tightening Adjustment

 Check that the POWER LED is on.
 Check that the PWR LED is on.
 Check that the ALM1 LED is off.
 Check that the ALM2 LED is off.
 Check that the LBAT LED is off.
 Check that the IO CNT LED is on.
 Check that the RUN LED is on.
 Check that the ERR LED is off.
 Check that the IO CNT LED is on.
 Check that the ExT LED is on.
 Check that the FUSE LED is off.
 Check that the input LED goes on/off.
 Check that the output LED goes on/off.

Periodic Inspection

Perform inspections once every six months or more. The inspection items are as follows.

Item
Measurement of AC
supply voltage

The connection of allparts
Battery
Fuse

5.3

Content
 Measure the AC 100/200 V terminal voltage.(AC 85 to
264 V)
 Measure the terminal voltage of the DC 24 V external
power supply.
 Check that terminal screws are not loose. Check thatthe screws are not converging.
 Check that the LBAT LED is off. (If the LED is on,
replace the battery) Check that the FUSE LED is off. (If the LED is on,
replace the module or connect it to an external power
supply)Procedure Supply voltage
adjustment
 Supply voltage
adjustment
 Tightening Adjustment
 Replacement
 Replacement
 Check the external
power supply

Battery Replacement

Backup for the retain memory and clock is supplied for approximately 5 days by the supercapacitor after thesystem control power supply is switched off. Thereafter the battery is used. To ensure that the battery works
even for long power outages, as a preventive measure, replace it after about 5 years of accumulated outages.
Backup time: Approximately 5 days using the supercapacitor (25°C) and thereafter approximately 5 years using
the battery.
Backup time when a battery fault is detected: Approximately 5 days using the supercapacitor (25°C).

53http://www.toyodenki.co.jp/
HEAD OFFICE： Tokyo Tatemono Yaesu Bldg, 1-4-16 Yaesu, Chuoh-ku,
Tokyo, JapanZIP CODE 103-0028
TEL： +81-3-5202-8132 - 6
FAX： +81-3-5202-8150

Contents of this manual are subject to change without notice.