GA0001002_04

Signal Tower

TYPE LR6-IL

Complete Operation
ManualInstallation

Operation Maintenance

Page

Notice to Customer
Thank you very much for purchasing our PATLITE
products.
z Request the installation and wiring be performed bya professional contractor if construction work is
involved.
z Prior to installation, read this manual thoroughly
before using this product to ensure correct use.
z If there are any questions concerning this product,refer to the contact information at the end of thisdocument and contact your nearest PATLITE Sales
Representative.

To the Contractor
z Read this manual carefully prior to installation.
z Be sure to return this manual to the customer.

– 1 –1 Read this First22 Model Number Configuration

2

3 Names and Dimensions

3

4 Installation

4

5 Wiring

6

6 How to Use

7

7 Buzzer Settings

9

8 Detaching the Unit

10

9 Troubleshooting

22

10 Specifications

23

11 Service Parts

25

12 Optional Parts

26

1

Read this First
Safety Precautions

The safety precautions that should always be followed in order to prevent injury to user or other individuals as well as
prevent damage to property are described below.
 The level of injury or damage caused by ignoring these safety precautions and using the product improperly is categorized
and described below.

Warning

This icon indicates an action with the potential tocause death or serious injury.

CautionThis icon indicates an action with the potential tocause injury, physical loss or damage.

Warningz Request the installation and wiring be accompanied by a professional contractor. If installation is done improperly, it
may result in fire, electric shock, falling, or malfunction.

Cautionz Adhere to the items below to prevent a short or damage.
- Be sure that the product is disconnected from the power source when changing, replacing or adding a unit.
- Use this product in the proper state. (Replace parts such as the body or each unit if damaged.)z Avoid long exposure to the Buzzer sound from a close distance. Failure to observe this may lead from irritation topermanent damage to the ears. (When Buzzer Unit is used)z In order to maintain protection of this product against dust and waterproofing performance, be sure to use the head
cover, LED unit and buzzer unit in the condition that it was originally attached.
z To ensure the waterproofing performance of this product, do not remove the O-ring or the waterproof packing. Dust
and waterproofing performance will decrease.
z When removing covers or packing from the equipment, which is attached to this product, be careful not to snag the
product. Failure to comply may result in damage to the product.

Noticez To ensure proper safety while using the signal tower, observe the following:- Perform periodic pre-maintenance.
- As a precaution against problems occurring, use this product together with other equipment.
z Be sure to prevent electrostatic damage due to discharge when working with this product for wiring, exchanging
units, setting up parameters, etc. by discharging static electricity on your body, etc.
(To prevent damage from static electricity, touch hands or other body parts to metals or an earth ground to discharge
the body from static charge.)z Use a soft cloth, etc., dampened with water to wipe the main unit. If wiped with chemicals outside water (thinner,benzine, gasoline, oil, etc.), product damage may occur.
z To ensure safety when this product is installed onto equipment, observe the following:- Do not remove parts beyond those designed to be removed from this product.
- Do not modify or disassemble this product.
- Use only the specified replacement parts listed in this document.

2

Model Number Configuration
Model

Tiers

Extended
Functionality

Mounting/
WiringBuzzer

Body
Color

3

IL

WM

N

W

Assembly Model

LR

6

-

Unit Model(Body Unit)

LR

6

-

IL

WM

N

W

Unit Model(Body Unit)

LR

6

-

IL

WC

N

W

6 Φ60

3 Tiers

N No Flashing

IL IO-Link

W Off-white

WM Direct Mount / M12 Connector (Mounting with 3 Hexagon Bolts)
WC Direct Mount / M12 Connector (Mounting with M30 Nut)
– 2 –LED Unit
Color

-

RYG

LED Color: R (Red) / Y (Amber) / G (Green)(From top to bottom)

3Names and Dimensions

 WM Direct Mount/M12 Connector Specifications (3-point Screw Attachment)(Unit: mm)

No.
LR6-3ILWMNW
Φ60
1
2

1

Part Name

Material

Head CoverPC

2

LED Unit

Globe: PC

19

3

Body

PC

40

4

M12 Bracket

PC

5

Direct Mount Bracket

PC

6

Waterproof Packing

Silicone Rubber271*M12 connector cable is sold separately.
(Please use an M12 connector of Φ16 or less.)

3
4

Accessory

5LR6 - WM
Flanged nut (M4)126

3 pcs.

LR6-ILWMNW
Φ60
1

19

3
4

132

5

12

6

 WC Direct Mount/M12 Connector Specifications (M30 Nut Attachment)(Unit: mm)

No.
LR6-ILWCNW
Φ60
1

19

2
3

107

4

10

5

Material

Head Cover

PC

2

Body

PC
PC

3

M12 Bracket

4

Direct Mount Bracket

PC

5

Waterproof Packing

Silicone Rubber

6

M30 Nut

PC*M12 connector cable is sold separately.
(Please use an M12 connector of Φ16 or less.)

25

6

Φ52

Part Name

1

M30 × 1.5
1/2” NPT Internal
Threads– 3 –4Installation
Noticez The following requirements are necessary for a proper mounting location.
- Location with strong and even surface with minimal vibration.
z Install with the mounting direction in the upright position.
z When the installation location is unavoidably irregular and waterproof performance is required, use a sealant between
the product and the installation surface.

Basic Mounting Instructions
holes for the mounting and wire-distribution for the product.
1 Make(Check the Model and refer to the suitable mounting dimension figure.)

2 Connect to the product through the distribution hole.
3 Secure the product with the nuts.
 WM WC Installation Figure (M12 Connector Installation Figure)Body
M12 Bracket
Connect to the M12
Connector through the
distribution hole.

1 Connect cabel
to the M12
Connector.

1

2 Turn theconnected
cable in the
direction of thearrow.

2

Direct Mount Bracket

 WM Mounting Dimensional Drawing(Unit: mm)
Mounting Hole
(3 places)

Screw/
Nut

Φ5

M4

120°
120°
Φ40

Recommended TorqueNameplate
Position

Wire Distribution Hole
(Φ20)

– 4 –

0.6 N·m WC Installation Figure (1/2” NPT Installation Figure)
While holding part ‘A’, install the 1/2” NPT.
Failure to comply may result in damage.

A

A

1/2” NPT

Recommended Torque2.25 N·m Mounting Dimensional Drawing(Unit: mm)
28.5

Mounting Hole

Nut

Φ31

M30

15°

Recommended Torque4.5 N·m

Nameplate
Position

– 5 –

5

WiringWarningz Ensure the proper working voltage is used and that direct current or alternating current is properly applied.
Any mistake in wiring may result in damage or fire.

Cautionz Do not pull the wire, or stuff it inside of this product. Possible cause of failure may occur.

Wiring Example and M12 Connector Pin Layout
 Wiring Example

 M12 Connector Pin Layout
L+

N.C.

N.C.

IO-Link Master
L+ (Pin-1)
IO-Link C/Q (Pin-4)
L- (Pin-3)

L+
C/Q
L-

M12 Connecter

– 6 –

L-

IO-Link C/Q

Connector type: M12, 5-pins, A code

6

How to UseThis product is an IO-Link compliant product.
Connect this product by following the “ 5 Wiring” (p. 6).
The controller can light, flash or extinguish the LEDs or control the buzzer.
Changing the “Operating Mode” settings enables the following modes:
z Simple Modez Advanced Mode Simple Mode
This mode performs simple control by only turning ON and OFF each LED and the buzzer.
Other settings are specified using the parameters.
Send the processed data by referring to the table below.
bit 0
Byte 0 data

LED Unit (Red)ON / OFF

Byte 1 data

LED Unit (Amber)
ON / OFF

Byte 2 data

LED Unit (Green)
ON / OFF

Byte 3 data

LED Unit (Blue)ON / OFF

Byte 4 data

LED Unit (White)
ON / OFF

Byte 5 data

BuzzerON / OFF

bit 1

bit 2

bit 3

bit 4

bit 5

bit 6

bit 7

Not usedNot usedNot usedNot usedNot usedNot usedNot used Advanced Mode
This mode performs advanced control such as lighting, flashing, and turning off each LED as well as sounding,intermittently beeping, or stopping the buzzer.
Other settings are specified using the parameters.
Send the processed data by referring to the table below.
Enable the intermittent buzzer settings to repeatedly sound the buzzer for 500 ms and stop the buzzer for 500 ms.
Refer to (p. 8) for the pattern of each LED.
bit 0

bit 1

bit 2

bit 3

bit 4

bit 5

bit 6

bit 7

Byte 0 data

LED Unit (Red)ON / OFFNot used

LED pattern (Red)

Not used

Byte 1 data

LED Unit (Amber)
ON / OFFNot used

LED pattern (Amber)

Not used

Byte 2 data

LED Unit (Green)
ON / OFFNot used

LED pattern (Green)

Not used

Byte 3 data

LED Unit (Blue)ON / OFFNot used

LED pattern (Blue)Not used

Byte 4 data

LED Unit (White)
ON / OFFNot used

LED pattern (White)

Not used

Byte 5 data

BuzzerON / OFFNot used– 7 –Intermittent
Buzzer

Not used LED Pattern
Setting

Description

0

Lit

1

1 sec. Flash (Slow)

2

500 ms Flash (Medium)3

250 ms Flash (Fast)

4

Single Flash5

Double Flash6

Triple Flash

Example:Byte 0 data = 0
 1h Red Light
Byte 1 data = 1
 1h Amber Flashing(1 sec Cycle)
Byte 2 data = 3
 1h Green Flashing(250 ms Cycle)
Byte 3 data = 6
 1h Blue Triple
Flash
Byte 4 data = 0
 0h White OFF
Byte 5 data = 1
 1h Intermittent
Buzzer

Noticez Settings 4, 5 and 6 cannot be used with the Multicolor LR6-E-MZ of the LED Unit.
Each LED may not light correctly.
z Settings 4, 5 and 6 cannot be used with the WD transmitter for the wireless data communication system.
The correct data may not be acquired.
z The intermittent buzzer and the LED pattern do not synchronize.

 Parameter Settings
For information about the parameter settings, please download the IODD from the LR6-IL page on our homepage (https://www.patlite.com/).
Please also download and use the parameter sheet in the same way.

– 8 –

7

Buzzer Settingsz Do not use excess force when performing operations. Failure to comply will result in damage due
to breakage or deformation.
z Do not use sharp-pointed objects to perform operations. Failure to comply may result in damage
and inoperative switches or hinder contact between contact parts.

CautionBuzzer Unit
Bottom View

■ Indicates the position of the DIP
switch. (Down to turn “ON”.)

 DIP Switch Configuration Table
BuzzerSound

DIP Switch

DIP Switch

Sound Pattern

3

Volume

1

2

No. 1

OFF

OFF

Rapid intermittent beep
(call sign)

OFF

Normal

No. 2

ON

OFF

Continuous beep soundON

Noise reduction

No. 3

OFF

ON

Rapid hi-low

No. 4

ON

ON

Sweep soundNote: DIP Switch 4 is not used.
The factory default settings have all of the DIP
switches in the “OFF” (Up) position.

– 9 –

8

Detaching the Unit

Follow the procedure below to detach a unit, such as when removing the Buzzer Unit or changing the layout of the LED
Units.

Link to Video

Cautionz Be sure that it is disconnected from the power source before working on it.
z Do not apply excessive torque or strong shock to each unit or body. Failure to comply will result in damage or
malfunction.
z Do not touch the connector area or the inside of the body and LED unit. Failure to comply will result in damage or
malfunction.
z Be sure to lock each unit securely when attaching. Failure to comply will result in damage or malfunction.
z Detach the unit in the following manner. Any other method may result in damaging the product.
Attachment: Attach one unit at a time to the body.
Removal: Firmly hold the bottom section while removing the upper section.

Please attach each unit
from the Body Unit one ata time.
Units may become
damaged if attached fromthe top side.

Noticez The maximum number of attachment units per product are five LED units, plus one buzzer unit.
z When using the Multi-Color LED Unit LR6-E-MZ for the LR6 (60 mm) Signal Tower, the maximum number of attachment
units per product is one LED unit and one buzzer unit.
z When using Wireless Data Acquisition System WD, the maximum number of attachment units per product are three
LED units.

– 10 –

<LED/Buzzer Unit> Removal

LED Unit or Buzzer Unit

Turn the body or LED unit counter-clockwise to unlock,then raise upwards to remove it.
 Positioning Mark
<Locked><Unlocked>

Body or LED Unit

 Attachment

Align the Positioning Mark after insertion, then turn theunit clockwise to lock it.

Align the positioning marks
after attachment.

 Positioning Mark
<Unlocked>– 11 –<Locked><Body Unit> Removal

While holding the Direct Mount Bracket, turn the M12
Bracket counter-clockwise, until it unlocks, then pull it
upwards to remove.
M12 Bracket

 Positioning Mark
<Locked><Unlocked>

Direct Mount
Bracket Attachment

Align the Positioning Mark after insertion, then turn theunit clockwise to lock it.

Align the positioning marks
after attachment.

 Positioning Mark
<Unlocked>– 12 –<Locked>

<Troubleshooting the Buzzer Unit Attachment>
The Buzzer Unit is generally in the status shown in the diagram below after removal.

Buzzer Unit

Rib

GroovePositioningMark
LED Unit

Buzzer Unit
(Detached)
Bottom View

Body

The rib inside of the Buzzer Unit fits into the groove when the
Buzzer Unit has been removed from the product.

CautionCheck to make sure the rib inside of the Buzzer Unit fits into the groove if the Buzzer Unit does not attach properly. Attach
the Buzzer Unit by referring to the next page if the rib does not fit into the groove as shown in the diagram below.
In addition, the rib may slide out of the groove during removal as shown in the diagram below depending on how the
Buzzer Unit was removed.
Attaching the Buzzer Unit to the product again in this state may result in damage.

GrooveRib

Buzzer Unit
Bottom View

– 13 –

Use the procedure below if the Buzzer Unit does not attach properly.

Turn the part inside the Buzzer Unit in the counter-clockwise direction.
Turn until the rib fits into the groove, then attach the Buzzer Unit to the
product.

Turn this part in the
counter-clockwise direction.

Rib

GrooveBuzzer Unit
Bottom View

– 14 –

<Example for LED Unit Reconfiguration>
 Moving an LED Unit lower

1 Remove the LED Unit right above the LED
Unit in the area to remove.

3 Align the positioning marks and insert the LED
Unit that was removed in 1 , then turn the
LED Unit clockwise to lock it in place.

– 15 –

2 Turn the LED Unit to remove counterclockwise while holding the adjacent LED unit
to release the lock, then pull upward.

 Adding an LED Unit

1 Remove the LED Unit above the area toattach an additional LED unit.

3 Align the positioning marks and insert the LED
Unit that was removed in 1 , then turn the
LED Unit clockwise to lock it in place.

– 16 –

2 Align the positioning marks and insert the
LED Unit, then turn the LED Unit
clockwise to lock it in place.

 Changing the Position of an LED Unit

1 Remove the LED Unit right above the
LED Unit that will be changing postitions.

2 Remove the LED Unit that will be changing
positions.

3 Remove the LED Unit right above theposition to add the LED unit.

4 Attach the LED Unit that was removed in 2 .

– 17 –

5 Attach the LED Unit that wasremoved in 3 .

6 Attach the LED Unit that wasremoved in 1 .

– 18 –

<Troubleshooting the LED Unit>
The structure of the LED Unit is indicated below.
StatusCondition
Lens
LED Unit

Rib/Groove

Positioning
Mark

Body

Rib/Groove

LED Unit(Detached)
Top View

The rib of the lens generally fits into the groove when the LED Unit has been
removed from the product.
Lens

Rib
GrooveLED Unit

Positioning
Mark

Rib

Body

GrooveLED Unit(Detached)
Top View
The rib of the lens generally does not sit in the groove while the LED Unit is
attached to the product.

– 19 –

Caution
Check whether the rib of the lens inside of the LED Unit fits into the groove if the LED Unit does not attach properly. Attach
the LED Unit by referring to the next page if the rib does not fit into the groove as shown in the diagram below.
In addition, the rib may slide out of the groove during removal as shown in the diagram below depending on how the LED
Unit is removed.
Attaching the LED Unit to the product again in this state may result in damage.
Lens

Rib
GrooveRib

LED Unit
Top View

GrooveDo not remove the LED unit as shown in below.
The rib of the lens will slide out of the groove.
Attaching the LED Unit to the product again in this state may result in damage.

1 Remove multiple
LED units at thesame time.

2 Remove the target LED
Unit from the multiple
LED Units that havebeen removed.

– 20 –The rib of the lens slides
out of the groove.

Use the procedure below if the LED Unit does not attach properly.

Turn the lens inside the LED Unit in the counter-clockwise
direction.
Turn until the lens snaps in place, and then attach the LED
Unit to the product.

Lens

LED Unit
Bottom View
Lens
Rib/Groove

Rib/Groove

LED Unit(Attachable Status)
Top View– 21 –

9

Troubleshooting

Troubleshoot problems that occur by following the instructions in the table below.
No.
1

2

3

4

5

Problem
The LED does not light.

The color of the LED
differs from the desiredcolor.

Confirmation

RemedyHas the wiring been connected properly?

Wire the LED again while referring to the
instructions in “ 5 Wiring” (p. 6).

Is the power source supplying the proper
voltage and current?

Check whether the connected IO-Link is
putting out the proper voltage.

Is the processing data correct?

Refer to the instructions in “ 6 How toUse” (p. 7-8). and resend theprocessing data.

Send processing data compatible with the
Is a custom independent color control unit color selected in the control instead of thebeing used?
light color for the independent color
control unit.
Is the processing data correct?

Refer to the instructions in “ 6 How toUse” (p. 7-8). and resend theprocessing data.

Are the parameters correct?

Specify the parameters while referring to
the instructions in “ 6 How to Use”
(p. 7-8).

The LED does not flash.

The sound of the buzzer
is low.

Adjust the volume while referring to the
Are the volume settings for the buzzer too
instructions in “ 7 Buzzer Settings”
low?
(p. 9).
Is the processing data correct?

Send the process data while referring to
the instructions in “ 6 How to Use”
(p. 7-8).

Is the Buzzer Unit attached?

The Buzzer Unit is an optional part.
Check “12 Optional Parts” (p. 27), andthen attach the Buzzer Unit to the productby referring to “ 8 Detaching the Unit”(p. 10-21).

The buzzer does notsound.

Check the “Information for Inquiries,” and then contact the nearest PATLITE Sales Representative if you cannot resolve theproblem even after the above troubleshooting.
Information for Inquiries
Product Name

IO-Link Signal Tower

Date of Purchase

/   /

Model

(→ 2 Model Number
Configuration [p. 2])

ProblemPlease provide as much detailas possible.

– 22 –

10 Specifications
General Specifications
Model

LR6-3ILWMNW-RYG

Rated Voltage

24 V DC

Voltage tolerance range

18 V DC to 30 V DC

Rated current consumption
Rated power consumption

Standard

170 mA

Maximum

200 mA

Standard

4W

Maximum

5W

Inrush current

10 A / 0.3 msec

Ambient operating temperature-20 °C to +50 °C

Ambient operating humidity

90 % RH or less; No condensation

Ambient storage temperature-30 °C to +60 °C

Ambient storage humidity

90 % RH or less; No condensation

Installation location

Indoor

Installation direction

Upright direction

Protection Rating
Environmental
conditions

IP65, NEMA TYPE 4X, 13
When installed in the upright direction

Insulation resistance

5 MΩ or more at 500 V DC between charging parts and non-charging metal parts

Withstanding voltage

1 minute at 500 V AC between charging parts and non-charging metal parts

Mass (Tolerance: ±10 %)0.38 kg

Exterior dimensions

See “ 3 Names and Dimensions”

Compliance standards

UL 508, CSA-C22.2 No. 14, EMC Directive (EN 61000-6-4, EN 61000-6-2)
RoHS Directive (EN 50581), FCC Part 15 Subpart B Class A
KC (KN 61000-6-4, KN 61000-6-2)

Notes

The brightness of each LED may differ according to the characteristics of the LED or color variations in eachindividual LED or the product.

Function- LED control- Buzzer control- Operational mode/pattern settings- LED flashing/intermittent- Buzzer Pattern Settings

Communication
Specification

IO-Link revision

1.1

Transmission speed

COM2 (38.4 kbps)

Minimum cycle time

8 ms

Processing data
length

6 byte / 0 byte (input from master / output to master)

Vendor ID

763

Device ID

80001

The requirements in each law and regulation are only included in the language designated by each law and regulation.
Check the instruction manuals published in each language.

– 23 –

Model

LR6-ILWMNW

LR6-ILWCNW

Rated Voltage

24 V DC

Voltage tolerance range
Rated current consumption
Rated power consumption

18 V DC to 30 V DC
Standard

170 mA

Maximum

200 mA

Standard

4W

Maximum

5W

Inrush current

10 A / 0.3 msec

Ambient operating temperature-20 °C to +50 °C

Ambient operating humidity

90 % RH or less; No condensation

Ambient storage temperature-30 °C to +60 °C

Ambient storage humidity

90 % RH or less; No condensation

Installation location

Indoor

Installation direction

Upright direction

Protection Rating

IP65, NEMA TYPE 4X, 13

Environmental
conditions

When installed in the upright direction

Insulation resistance

5 MΩ or more at 500 V DC between charging parts and non-charging metal parts

Withstanding voltage

1 minute at 500 V AC between charging parts and non-charging metal parts

Mass (Tolerance: ±10 %)0.2 kg0.16 kg

Exterior dimensions

See “ 3 Names and Dimensions”

Compliance standards

UL 508, CSA-C22.2 No. 14, EMC Directive (EN 61000-6-4, EN 61000-6-2)
RoHS Directive (EN 50581), FCC Part 15 Subpart B Class A
KC (KN 61000-6-4, KN 61000-6-2)

Function- LED control- Buzzer control- Operational mode/pattern settings- LED flashing/intermittent- Buzzer Pattern Settings

Communication
Specification

IO-Link revision

1.1

Transmission speed

COM2 (38.4 kbps)

Minimum cycle time

8 ms

Processing data
length

6 byte / 0 byte (input from master / output to master)

Vendor ID

763

Device ID

80001

The requirements in each law and regulation are only included in the language designated by each law and regulation.
Check the instruction manuals published in each language.

– 24 –

11 Service Parts
These are the various parts for the customer to use when repairing or replacing parts for the product.
O-ring 60

Head Cover 60 [W/A]

Shading Sheet 60

5 pcs.

5 pcs.

– 25 –

12 Optional Parts
The optional parts for this product are listed below. (Top line: Part Name; Bottom: Model)

Model Number Configuration

LED Unit
LR6-E

LED Unit
Color

Model
Model Number

LR

Globe
Color

6 - E -

* LR6 - Z

R Red
Y Amber
G Green
B BlueC WhiteM Multicolor*(None) Colored GlobeZ Clear Globe

External Diagram

General Specifications(Unit: mm)

(10)

40

Model

LR6-E-□□

Ambient operating
temperature-20 °C to +50 °C

Ambient operating humidity

90 % RH or less; No condensation

Mass(Tolerance: ±10 %)0.060 kg

Notes

φ60

– 26 –The brightness of each LED may differ according to thecharacteristics of the LED or color variations in eachindividual LED or the product.

Model Number Configuration

Buzzer Unit
LR6-BW

Body Color(Material)

Model
Model Number

LR

6 - B

W

W Off-white (PC)

External Diagram

General Specifications(Unit: mm)

53.5

Model

LR6-BW

Ambient operating
temperature-20 °C to +50 °C

Ambient operating humidity

90 % RH or less; No condensation

Mass(Tolerance: ±10 %)0.060 kg

Buzzer sound/frequency (typ.)No. 1

Rapid intermittent beep (call sign) / 3378 Hz

No. 2

Continuous beep sound / 3378 Hz

No. 3

Rapid hi-low / 2016 Hz & 3012 Hz

No. 4

Sweep sound / 1000 Hz - 4032 Hz

Sound pressure level

φ60
Environmental
conditions– 27 –

Typ. 84 dB

Noise reduction approx. -10 dB
Toggle with DIP switch
See “ 7 Buzzer Settings”

Buzzer sound: No. 4 Sweep sound measured from a
distance of 1m in a total circumference from the buzzer
source.

Wireless Data
Communication System
Transmitter

Model Number Configuration

WDT-6LR-Z2
Model Number

Model

Compatible
Product

WDT -

6LR

- Z2

6LR LR Model Signal Tower Size: Φ60

External Diagram

General Specifications(Unit: mm)

Model

10

70

WDT-6LR-Z2

Ambient operating
temperature-20 °C to +50 °C

Ambient operating humidity

85 % RH or less; No condensation

Mass(Tolerance: ±10 %)0.085 kgCommunication standard

IEEE 802.15.4 (Wireless communication)

Communication frequency

2405 MHz to 2480 MHz (16 channels)

Communication distance

Estimated to be approx. 30 m (Reference value)

φ60– 28 –

The optional parts for attachment are listed in the following table:

Pole Bracket

Wall Mounting Bracket

Wall Mounting Bracket

SZP-004W

SZK-001U

SZK-003W

Mounting Bracket

Mounting Bracket

Aluminum PoleSZ-010

SZ-016A

POLE-[100/300/800]A21

Mounting Bracket
SZW-002W– 29 –

– 30 –