Mitsubishi Heavy Industries Technical Review Vol. 53 No. 1 (March 2016)
2Start of Business Operations ofResource Recycling Waste Treatment Facility(Stoker Type Incinerator) with SMASH System®

Mitsubishi Heavy Industries Environmental& Chemical Engineering Co., Ltd.

The latest waste treatment facility using the SMASH (SMart ASH treatment) system, theIwate Chubu Clean Center (hereinafter referred to as the facility), started business operations inOctober 2015. The facility features a number of the latest resource recycling systems in addition tothe "SMASH System®" developed by Mitsubishi Heavy Industries Environmental & ChemicalEngineering Co., Ltd. (MHIEC). The SMASH System® allows the recycling of incinerated ash as acement resource, helping the entire facility make a contribution to global environmental
conservation. In this article, the features of the facility and the actual operation status are reported.

|1. Facility overview
An overview of the facility is described in Table 1, and the schematic flow is shown inFigure 1. The Design-Build-Operate (DBO) model was adopted as the business operation scheme.
MHIEC constructed the plant body, and Iwate Chubu Eco Creation K.K., which is a special
purpose company (SPC) wholly-owned by the MHIEC group, operates the facility. The incineratorof the facility is a complete continuous incinerator (stoker incinerator) with a rated treatment
capacity of 182t/day (91t/day x 2 incinerators). The waste incineration heat is recovered by a boiler
and used as the superheated steam of 4.0MPa and 400°C for the generation of electricity in a steam
turbine, generating a maximum of 4,100 kW of electricity. The power generated covers the needsof the facility and the excess electricity is supplied externally (as power for sale).
Table 1
Facility nameCompletion year
Incinerator type
Nominal treatment capacity
Gas-cooling method
Power generation equipment
Planned value of incinerated ash output

Figure 1

Facility overview
Iwate Chubu Clean Center
September 2015
Complete continuous incinerator (stoker furnace)
182 t/day (91 t/day × 2 furnaces)
Waste heat boiler (4.0 MPa, 400°C)
Condensing extraction turbine (4,100 kW)
10 t/day (when 2 furnaces are operated)

Schematic flow of treatment at Iwate Chubu Clean CenterMitsubishi Heavy Industries Technical Review 53 No. 1 (March 2016)3|2. Features of the facilityDescribed below are the features of the facility including the SMASH System®, the IGRsystem, a large-scale photovoltaic power generation system and a self-sustaining infrastructure
facility intended as a disaster prevention base.
(1) SMASH System®
This system is comprised of a washing tank, pH controlling equipment and othercomponents. The treatment flow is shown in Figure 2. The incinerated ash from which
valuables such as metals were recovered by the pre-treatment equipment is stirred and washedin the washing tank. Next, water adhering to the washed ash is removed, and the ash is thenconveyed to the washed ash pit.

Figure 2

Flow of treatment by SMASH System®

The chlorine contents of eco-cement and eco-cement products of normal quality are
specified as 0.1% or less in JISR5214 and 0.035% or less in JISR5210, respectively. Since
incinerated ash normally contains 1% to 2% chlorine, the amount of incinerated ash that can bemixed with cement material is limited. On the other hand, as shown in Figure 3, whichindicates the dechlorination effect obtained by the actual operation of the SMASH System®, itwas confirmed that the washing of ash with water can reduce the concentration of chlorine toapproximately 0.2%.

Figure 3 Dechlorination effect by SMASH System®

The content of chlorine in incinerated ash is reduced and the dispersion in chlorine
concentration is reduced.

Not only can the SMASH System® reduce the concentration of chlorine in incinerated
ash, it can also reduce the dispersion in the concentration of chlorine, from the wide range of0.60% to 1.50% before washing to the range of 0.10% to 0.40%. This facilitates themanagement of the incinerated ash mixing ratio in the cement production process. As a result,the mixing ratio of incinerated ash in cement can be raised to increase the amount of incinerated

Mitsubishi Heavy Industries Technical Review 53 No. 1 (March 2016)4

ash that can be accepted by a cement plant.
All the incinerated ash discharged from the facility is subjected to water washingtreatment in the SMASH System® and the washed ash is received by the Mitsubishi Materials
Corporation Iwate Plant to be recycled as raw material for cement.
(2) Internal Gas Recirculation (IGR) system
The flow of this system is shown in Figure 4. The IGR system uses and circulates, as thesecondary combustion air, the combustion gas with a high oxygen concentration at theember-burning part after the stoker, thereby eliminating a secondary air blower and allowing
low air ratio operation with a reduced amount of combustible air. Low air ratio operation canreduce the amount of exhaust gas and provide highly efficient heat recovery.

Figure 4

Flow of IGR System

The exhaust gas in a furnace (oxygen concentration of 20%) at thecombustion part after the stoker is used and circulated as secondary air.

The operation status while the IGR system is operating is shown in Figure 5. It was
confirmed that by combining the IGR system and the latest combustion control system, stable
operation can be facilitated even in the low air ratio condition (air excess ratio Note 1) : about
1.35) and the amount of electricity that could be sold for each ton of waste increased by about
4% compared to existing operations.
Note 1) Air excess ratio: Ratio obtained by dividing the mass of actually supplied air by the mass oftheoretically required airFigure 5

Stability of combustion during low air ratio operation

Stable operation was observed at (air excess ratio) λ= about 1.35.

Mitsubishi Heavy Industries Technical Review 53 No. 1 (March 2016)
5(3)Large-scale photovoltaic power generation system
The empty space on the facility grounds was effectively utilized to set up a large-scale
photovoltaic power generation system, which is the symbol of renewable energy use (Figure 6).
This equipment generates an estimated 90 MWh annually. In October 2015 when business
operations started, the actual amount of power generated was about 6 MWh.
The facility contributes to the realization of a low carbon society through photovoltaicgeneration and highly efficient power generation (through the effective use of waste energy), as
well as by operating a "snow room" as a natural refrigerator that is used as a cold air source for
air conditioning in the summer season.

Figure 6(4)Photovoltaic power generation system

Self-sustaining infrastructure facility serving as a disaster prevention base
Recently, facilities that can serve as disaster prevention bases in the event of emergencies
and contribute to local communities are in demand.
At the facility, even if a power failure occurs in the event of a disaster, the large-capacity
private diesel power generation system can start the plant, and the steam turbine power
generation system allows self-sustained operation, so that the facility can continue functioning
as a waste treatment facility and a disaster prevention base. In simulation testing under theassumption that a power failure had actually occurred, it was confirmed that the plant could bestarted using only the electricity produced by the emergency power generator, andself-sustained operation could be performed by the turbine power generation system.
Furthermore, in combination with the storage batteries (large lithium ion batteries), thephotovoltaic power generation system allows the facility to secure the electricity required fordaily life even when the waste power generation is disabled. Thus, the facility can contribute to
the local community as a disaster prevention base.