Bulletin No. MCE-B 5102J

General Specifications

Model 3800
MULTI-SPRING TYPE DIAPHRAGM ACTUATORS
Model 3800 diaphragm actuator iscapable of controlling valve travel precisely by adjusting input air pressure
resulting in balance of the diaphragm
force and the spring force.
Model 3800 diaphragm actuator isnew-type actuator which is designed tobe compact and light weight by adopting
multi-spring structure.

Direct Action（DA）

Reverse Action（RA）（Air-to stem down）（Air-to stem up）

1. SPECIFICATIONS
Type

Model 3800 Pneumatic single action diaphragm actuator

ActionDirect action（DA）, Reverse action（RA）

Actuator Sizes

N24

N28

N33S

N40

Max Stroke（mm）

25383865

2120（216）

2750（280）

4040（412）

5690（580）

Power thrust N（kgf）
at off-balance 80kPa（0.8kgf/cm2G）

Hysteresis Error（With positioner） Max.
Linearity

1% F.S. … PTFE V Ring

（With positioner） Max. ± 1% F.S. … PTFE V Ring

Materials

Max.

（3）

2% F.S. …… Other Gland Packing

Max. ± 2% F.S. …… Other Gland Packing

Diaphragm

Cloth reinforced chloroprene rubber（※ Ethylene propylene rubber）

YokeFC200（※ SCPH2）

Spring Range kPa（kgf/cm2G）（5）※ 120 〜 280（1.2 〜 2.8），※ 40 〜 120（0.4 〜 1.2）
20 〜 100（0.2 〜 1.0），40 〜 200（0.4 〜 2.0），80 〜 200（0.8 〜 2.0），

Air Connection

Rc 1/4（※ NPT 1/4）

Ambient Temperature（4）− 20 ℃〜＋ 70 ℃（※− 50 ℃〜− 20 ℃，＋ 70 ℃〜＋ 100 ℃）

Dimensions, Mass

See page 2 Table 1.

Painting Color

Silver※Options

Additional
Mechanisms

Top-mounted handwheel, Side-mounted handwheel, Travel stop.

Accessories

Pneumatic positioner（PA92A）, Electro-pneumatic positioner（EA91A, EA90A）,Air Filter regulator（MR2000）, Limit switch, Solenoid valve, Booster relay,
Speed controller, Lock up valve, Position Transmitter【Notes】（1）※ Manufactured and attached as option by customer s request.
（2）Material desingnation is represented by new JIS（SI unit）. Please consent in advance that approval drawings and other documents may represent with old material designation.
（3）The actuator for size N40, stroke 65 mm and spring range 80 〜 200kPa（0.8 〜 2.0kgf/cm2G）is not available.
（4）For ambient temperature, denoted the extended temperature range as option.
＆ Spring Range 120 〜 280kPa（1.2 〜 2.8kgf/cm2G）are available for only Actuator（5）Supply Air Pressure 400kPa（4.0kgf/cm2G）
Size N33S ＆ N40.

3800

Supply Air Pressure kPa（kgf/cm2G） 140（1.4）, 240（2.4）, 280（2.8）, 300（3.0）,（5）※ 400（4.0）

1Model No. 3800
■ Table 1. Dimensions and MassActuator Size

N 24

N 28

N 33 S

N 40

Effective Diaphragm Area（cm2）

270

350

515

725

Max. Diaphragm Chamber Volume（DA, RA）
（cm3）

1550

2820

4510

9090

Outside Dia.
of Diaphragm Casing φ D

240280330

400

DA ； HD297336391515

RA ； HR321

360415539

DA ； WD

158

171183272

RA ； WR133

133145207

M 12 × 1.75

M 18 × 2.0HeightStem Length

M 9 × 1.25

Thread of valve stem
Yoke Insertion Dia.
Yoke Thickness

φY60

100

T

2040

Yoke nut

Yoke bolt
6-φ 19 PCD 135

Yoke Mounted by
Yoke Seat Dia.
Approximate Mass

φa85

85

85

170（kg）

12152451

DA

Air connector

Exh. hole

RAExh. hole

Actuator Size N403800

Air connector

2Model No. 3800

2. ADDITIONAL MECHANISMS1 Top-mounted Handwheels■ Table 2. Dimensions and Mass for DA type with Top-mounted Handwheel
Unit ： mm
N24Actuator Size

N28200Handwheel Dia. φ B

N33S

N40250300469535626795

Max. Stroke

25383865

Turns for Max. Stroke

17252543

Approximate Mass（kg）

16203165

Max. HeightHD■ Table 3. Dimensions and Mass for RA type with Top-mounted Handwheel
Unit ： mm
N24Actuator Size

N28250Handwheel Dia. φ B

N33S

N40300400562628706922

Max. Stroke

25383865

Turns for Max. Stroke

8131322Approximate Mass（kg）

1822

34

71

Max. HeightHR

2 Side-mounted Handwheels■ Table 4. Dimensions and Mass for units with Side-mounted Handwheel
Unit ： mmActuator Size

N24Handwheel Dia. φ B

250

Handwheel
Projection

S

235

271

271

402

DA；WD（2）Stem
Length RA；WR（2）

138

151

163

235

125

170

Center-to-center distance M

6351

59

65

Max. Stroke

2538

38

65

Turns for Max. Stroke

4.7

8.7

8.7

19

Approximate Mass（kg）

21

N33S
300

113

28

N40
400

37773800

N28【Notes】（1）Height HD and HR is coincident with thestandard actuator.
（2）Symbol WD and WR denote the same
dimension of attached figure on table 1.

3

Model No. 3800
3 Travel Stops
Travel stops are used to limit the valve travel if necessary.
＜ Example ＞
Actuator size N24, direct action, push-down close, to limit full open
N24 -DU-O
Valve travel limiting direction（O : Open, S : Shut）
Stem limiting direction（U : Upward, D : Downward）
Actuator action（D : Direct action, R : Reverse action）
Actuator size-DD--RD--DU--RU-■ Table 5. Classification of Travel Stop and Heights
ActuatorAction

Stem Limiting
Valve Travel
SymbolDirection
Limiting Direction

Open-O
Shut-S

Travel limit ofpush-down open

Open-O

Travel limit ofpush-down close-DD

Direct Action
（DA）

3800

Upward4Reverse Action
（RA）

-U

Actuator Size
Application
Travel limit ofpush-down close
Travel limit ofpush-down open

Shut-S
Downward-D-DU

Downward-D-RD

Shut-S

Travel limit ofpush-down close

Upward-RU

Open-O

Travel limit ofpush-down open

-U

Unit ： mm
Height
N24

N28

N33S

N40478531609778

HDHR

Model No. 3800

3. POSITIONER MOUNTING DIMENSIONS
1 Pneumatic Positioner Model PA92A
Actuator

Flow
Direction
Side-mounted
Handwheel

Actuator■ Table 6. Mounting Dimensions for Model PA92A
Unit ： mm
Actuator Size

N24

N28N33S

N40Actuator outside Dia. φD240

280

330

400Action

DARADA

RADA

RADA

RA

J

210

250

K330

270

【Note】The mounting dimensions for other positioner may be different from the above mentioned.

2 Electro-pneumatic Positioner Model EA91A, EA90A
Actuator

Flow
Direction
Side-mounted
Handwheel

Actuator■ Table 7. Mounting Dimensions for Model EA91A and EA90A
Unit ： mm
Actuator Size

N24N28N33S

N40Actuator outside Dia. φD240

280

330

400

DARADARADARADARAJ

220230K320360

3800

Action5

Bulletin No.MCE-B5102J

http://www.motoyama-cp.co.jp
本 社 工 場

Main Office & Factory

TEL（022）344-4511（代表） / FAX（022）344-4522
E-mail : info@motoyama-cp.co.jp
5-2, Ohira Aza Kameoka, Ohira-mura, Kurokawa-gun, Miyagi, 981-3697, Japan
TEL +81-22-344-4511 / FAX +81-22-344-4522
E-mail : info-overseas@motoyama-cp.co.jp〒981-3697 宮城県黒川郡大衡村大衡字亀岡５－２●販売・サービスネットワーク

東京支店〒210-0007 神奈川県川崎市川崎区駅前本町 10-5 クリエ川崎 11F

TEL（044）381-8770（代表） FAX（044）381-8772

大阪支店〒550-0014 大阪市西区北堀江 1 丁目 12-19 クリモトビル 3F

TEL（06）6535-8111（代表） FAX（06）6535-8655

国際営業部〒210-0007 神奈川県川崎市川崎区駅前本町 10-5 クリエ川崎 11F

TEL（044）381-8771

FAX（044）381-8773

札幌営

業所

〒001-0912 札幌市北区新琴似12条7丁目1-47
リバティタウンP棟101号

TEL（011）766-1520

FAX（011）766-1521

東

北営

業所

〒981-3697 宮城県黒川郡大衡村大衡字亀岡 5-2

TEL（022）344-1761

FAX（022）344-1762〒942-0036 新潟県上越市大字東中島2393番地

TEL（025）542-5151

FAX（025）542-5152〒290-0046 千葉県市原市岩崎西1丁目5-19

TEL（0436）21-4400

FAX（0436）21-3540〒422-8033 静岡市駿河区登呂4丁目28-5

TEL（054）269-5377

FAX（054）237-5855〒481-0012 愛知県北名古屋市久地野安田36番地

TEL（0568）26-6681

FAX（0568）26-6631〒710-0042 岡山県倉敷市二日市358

TEL(086)486-3381

FAX(086)486-3382

阪 神 サー ビ スセンター〒560-0894 大阪府豊中市勝部2丁目18-3

TEL（06）6854-7511

FAX（06）6854-7512

姫路

出張所

〒672-8014 兵庫県姫路市東山276番地1

TEL（079）263-8640

FAX（079）246-2130

徳山営

業所

〒745-0861 山口県周南市新地1丁目6-11

TEL（0834）21-5012

FAX（0834）31-0450〒792-0896 愛媛県新居浜市阿島1丁目6-26

TEL（0897）47-8993

FAX（0897）47-8995〒870-0108 大分市大字三佐字山ノ神980-1

TEL（097）527-3704

FAX（097）522-2352

TEL +86-411-6589-1277

FAX +86-411-6589-1278

大 衡 サービスセンター

上越営

業所

上 越 サービスセンター

関東営

業所

千 葉 サービスセンター

静岡営

業所

名 古 屋 営 業 所
中 部 サービスセンター

水島営

業所

周 南 サービスセンター

四国営

業所

新 居 浜 サービスセンター

大分営

業所

大 分 サービスセンター●海外関連会社本山阀门（大連）有限公司 〒116601 中国 遼寧省大連市金州新区港興大街 39 号 14-7
●海外販売代理店

中国、韓国、台湾、シンガポール、インドネシア、マレーシア、サウジアラビア●SALES AND SUPPORT NETWORK

Overseas Marketing & Sales Dept. : 11th Floor, Clie Kawasaki, 10-5, Ekimae-honcho, Kawasaki-ku, Kawasaki-city, Kanagawa, 210-0007 Japan
TEL: +81-44-381-8771
FAX : +81-44-381-8773
Domestic Sales Branches : Tokyo, Osaka, Sapporo, Tohoku, Joetsu, Kanto, Shizuoka, Nagoya, Hanshin, Tokuyama, Shikoku, Oita

●OVERSEAS AFFILIATED COMPANY

MOTOYAMA VALVE （DALIAN） CO., LTD
Gangxing Street 39-14-7, Jinzhou New District, Dalian-city, 116601 China

TEL: +86-411-6589-1277

FAX: +86-411-6589-1278●OVERSEAS NETWORK

China, Korea, Taiwan, Singapore, Indonesia, Malaysia, Saudi Arabia◆当社は保証期間を原則として製品納入後１年としています。
◆The product will be warranted for one year after delivering this product in principle.
■本カタログの記載内容は、商品の改良等のため予告なく変更することがありますので予めご了承下さい。
■MOTOYAMA is continuously improving and upgrading its product design, specifications and/or dimensions. Information included herein issubject to change without notice.

■本カタログは正しい情報の提供を目的としたものであり、本製品の市場性または適合性の保証を証明するものではありません。
■This catalog is supplied for information purpose only and should not be considered certified marketability and conformability of thisproduct.

202402 MSP