SPECIFICATIONSUL6703 MECHANICAL

MATERIALS

Operating Temperature
UL 6703-40 to 90°C

-40 to 194°F

Electrical
Current Rating (Amperes) UL 6703

Shell, Housing & Sealing Nut

PC / PBT

Lanyard		Nylon / Polyester

Contact Holders		

PBT - GF

Contact Retention Clip

Be-Cu

Latch / Screws		

Stainless Steel

Panel Gasket		 Silicone

8 AWG

37A

Voltage Rating

Sealing Gland		600V

Flammability		 UL94 V-0

UL Tested

Glow Wire		960°C (GWFI)		
825°F (GWIT)

Grounding
UL 2238, Sec 37.8

Weatherability		

Environmental Seal
UL6703

IP68 (mated only)

UL 746C F1Sockets		Copper
SC08-GH		Ag plating over Ni
SC08-SN		Ag plating over Ni
Pins		
Copper
PP08SGH		Ag plating over Ni
PC08SSN		Ag plating over Ni

UL1977 MECHANICAL

Silver = Ag

Environmental Seal
IEC 60529
UL 50EIP 68
UL Approved

Wire Size

8 AWG		 8.4 mm²

Operating Temperature
UL 1977-40 to 105°C		 -40 to 221°F

Mating Cycles (no load)

250 minMating Force (nominal)

28 lbf 		 125 N

Unmating Force

12 lbf		 53 N

Contact Retention Force (min)50 lbf		 222 N

Touch Safe (IEC 60529)

IP 20 (female side only)

Enclosure Ratings

UL 50E 4/4x *ElectricalCurrent Rating (Amperes)

UL 1977 		 CSA

8 AWG

60A		 40A

Voltage Rating
UL 1977 (AC/DC)

EPDM

Nickel = Ni

IEC 61984
ATTRIBUTESAMP Rating AC

60A

Voltage Rating AC

800V AC (operational)

Finger Safety **IEC 60529

Protection Degree

IP20 Unmated, IP68 Mated

Wire Size Tested

8 AWG

Contact Series Tested		

PC08SSN, PP08SGH SC08-SN, 		SC08-GH

Climatic Testing (Cold, Heat & MFG)

IEC 60512 Test -11j, 11i & 11g

Cycle Life		

IEC 60512 Test 9A - 5000 Cycles

Mechanical Strength Impact		IEC 60512 @ 29.5 Inches - 		dropped 8 times

Temperature Range-40 to 105°C, -40 to 221°F

600V

Grounding
UL 2238, Sec 37.8

Impedance

Contact Resistance (average)

0.300 Milliohms* Need stainless hardware - type 304 or 316

PROTECTION
Touch Safety with Finger Proof Housings & Wire Contacts* In mated and unmated condition, for standard 8 AWG wire contacts (only)** Female side unmatedIEC 60950-1
Creepage / Clearance per IEC 60950-1 9.55 (mated or unmated)
Material GroupIlla* In mated and unmated condition, for standard 8 AWG wire contacts (only)** Female side unmatedORDERING INFORMATIONSPEC Pak® is a highly configurable environmentally sealed connector. For convenience, follow the steps
below to determine component part numbers.
Step 1: Select Shell

Step 2: Select Sealing Gland		

PK1-076D05

PK6-076D05

Inline Receptacle Shell 		

Plug Shell* Define:

Number of Wires
Wires		- Discrete____________- Bundled____________

Wire OD__________________________* Select wire protection that will accommodate the number ofwires and outer diameter (OD) of the wire used in your application.
* Wire protection is required for use with inline receptacle shell(PK1-076D05) and plug shell (PK6-076D05) to obtain IP68 seal.

PK2-076D05

Panel Mount Receptacle & Gasket
Description

Part Numbers

Minimum Quantity

25

Inline Receptacle Shell

PK1-076D05

Plug Shell

PK6-076D05

Panel Mount Receptacle& Gasket

PK2-076D05

Receptacle Cover Kit

PK9-076 (shown on back page)

Plug Cover Kit

PK9P-076 (shown on back page)• Contact holders are available with multiple keys, please inquire.		
Numberof Holes

Cable Range Wire
Outer Diameter mm (in)MinimumQuantity
1Sealing Grommet
Part NumberOnly1020 mm (0.79)

B02266P7• For other wire configurations contact manufacturer
Wire Test Approval• Type TC-ER, 8 AWG 5/C sunlight resistant• Rated minimum 90°C dry: 90°C wet• 600V with outer diameter of cord 20 mm (0.79)
Torque Requirements• Hand tighten. Using a 44 mm wrench or strap wrench,tighten an additional 3/4—1 turn.
• 7.9 Nm (70 in- lb)

TEMPERATURE CHART - PER UL 1977

Step 3: Select Contacts

Solar 5 Posi�on Mid Power SPEC Pak®
Temperature Rise at Constant Current

SocketTemperature Rise
Above Ambient (°C)

60Pin

* Define:

Number of Circuits
Wire GaugeContacts			
- Power_______________________- Other_______________________			
Amps (continuous): ____ Max amps at ____ Volts

50403020100010203040
Amperes Applied

50

8 AWG 4 - Posi�on Under Load
8 AWG 5 - Posi�on Under Load

* Select power and/or ground contacts appropriate for your wire
size (AWG or mm²)
• Sockets are used in the receptacles(part numbers PK1-076D05 & PK2-076D05)• Pins are used in the plug(part number PK6-076D05)• Solid wires not recommended
Description

Part Numbers

Minimum Quantity

10Power Drawer 8 AWG Socket Crimp, Hot Plug/Ground

SC08-GH

Power Drawer® 8 AWG Socket Crimp, Standard Mate

SC08-SNPower Drawer 8 AWG Pin Crimp, Hot Plug/Ground

PP08SGHPower Drawer® 8 AWG Pin Crimp, Standard Mate

PC08SSN®

®

TOOLING INFORMATION
Wire Size

PartNumber

AWG MM ²PowerContact

Description

SC08-GH

POWER DRAWER CONT. 8 AWG
SOC.CRIMP, FIRST MATE GROUND

M22520/23-01 M22520/23-2 M22520/23-9

SC08-SNPOWER DRAWER CONT. 8 AWG
SOC.CRIMP, STD.MATE

M22520/23-01 M22520/23-2 M22520/23-9

PP08SGH

POWER DRAWER CONT. 8 AWG
PIN,CRIMP, STD.MATE, FIRST
MATE GROUND

PC08SSNPOWER DRAWER CONT. 8 AWG
PIN,CRIMP, STD.MATE

8 to 10 8.4 to 6.0

Crimp Tools
Pneumatic
Bench Tool + Die

1387G1

1388G6Daniels Mfg Tool *+ Locator OR Tool

1389G19DieLocator

M22520/23-01 M22520/23-2 M22520/23-9
M22520/23-01 M22520/23-2 M22520/23-9

M81969/14-06 INSERT AND EXTRACT TOOL
N/A

MID POWER SOLAR SPEC PAK
PKT-076TO1 RELEASE TOOL

* Must contact Daniels directly for this tooling option, www.dmctools.com

Pneumatic
Bench Tool
1387G1

Locator
1389G19

Release Tool
PKT-076T01

Die
1388G6
Slide posts
into the holeson the side

Insert & Extract Tool
M81969/14-06

DIMENSIONSPlug Shell | PK6-076D05
Top View			

Front View
[ 2.98 ]75.8[ 3.73 ]94.7[ 2.47 ]62.8

Side View			

Mated View

[ 3.09 ]99.1[ 4.35 ] 110.6
Mated Length to Panel
Receptacle

Panel Mount Receptacle & Gasket | PK2-076D05
Panel Cut Out

Front View

[ 2.36 ]60.0[ 3.19 ]81.0[ 0.75 ]R 19.0 (4)[ 2.36 ]60.0[ 2.13 ]54.0[ 3.19 ]81.0[ 2.3 ]
54.0

Side View

Mated View

[ 1.31 ][ 4.35 ] 110.6
Mated Length to Panel
Receptacle

33.2[ 0.98 ]25.0

Inline Receptacle Shell | PK1-076D05
Top View

Front View

Side View

Mated View

[ 2.83 ]71.8[ 3.76 ]95.5[ 6.89 ] 174.9
Mated Length to Plug[ 2.70 ]68.6[ 3.9 ]
100.0

Plug Cover Kit | PK9P-076
Front View			

Side View[ 3.03 ]77.0[ 1.10 ]28.0[ 2.52 ]63.9

Receptacle Cover Kit | PK9-076
Front View			

Side View[ 2.84 ]72.2[ 1.59 ]40.5[ 2.47 ]62.7* Covers are only for transporting conditions; not UL6703 approved.

Your Best Connection™
All Data Subject To Change Without Notice2020-0110 DS-MPSPAK5P-S REV 1

Anderson™ will use reasonable efforts to include accurate and up-to-date content in the data sheet. All product information contained in the data sheet including ordering information,
illustrations, specifications, and dimensions, are believed to be reliable as of the date of publishing, but is subject to change without notice. Anderson™ makes no warranty or representation
as to its accuracy. Content in the data sheet may contain technical inaccuracies, typographical errors and may be changed or updated without notice. Anderson™ may also make
improvements and/or changes to the products and/or to the programs described in the content at any time without notice. Current sales drawings and specifications are available
upon request.
©2021 Anderson Power Products, Inc. All rights reserved. SPEC Pak®, Power Drawer®, APP®, Anderson Power Products® and the APP logo are registered trademarks of Anderson Power Products,Inc. Anderson™ and Your Best Connection™ are trademarks of Anderson Power Products, Inc.
HEADQUARTERS: Anderson Power Products®, 13 Pratts Junction Road, Sterling, MA 01564-2305 USA T:978-422-3600 F:978-422-0128 • EUROPE: Anderson PowerProducts® Ltd., Unit 3, Europa Court, Europa Boulevard, Westbrook, Warrington, Cheshire, WA5 7TN United Kingdom T: +44 (0) 1925 428390 F: +44 (0) 1925 520203• ASIA / PACIFIC: IDEAL Anderson Asia Pacific Ltd., Unit 922-928 Topsail Plaza, 11 On Sum Street, Shatin N.T., Hong Kong T:+(852) 2636 0836 F:+(852) 2635 9036 •CHINA: IDEAL Anderson Technologies (Shenzhen) Ltd., Block A8 Tantou Western Industrial Park, Songgang Baoan District, Shenzhen, PR. China 518105 T: +(86) 755 2768
2118 F: +(86) 755 2768 2218 • TAIWAN: IDEAL Anderson Asia Pacific Ltd., Taiwan Branch, 4F.-2, No.116, Dadun 20th St., Situn District, Taichung City 407, Taiwan (R.O.C.)
T: +(886) 4 2310 6451 F:+(886) 4 2310 6460 • INDIA: IDEAL INDUSTRIES India Private Limited, 229-230, SPAZEDGE, Tower B, Sector 47, Sohna Road, Gurgaon – 122001,Haryana, India T: +(91) 956 007 5905 www.ideal-Industries.in • www.andersonpower.com