Bulletin No. MCE-B 5101I

General Specifications

Model 2800
SINGLE-SPRING TYPE DIAPHRAGM ACTUATORS
Model 2800 diaphragm actuators
provide the operation to control theDirect Action（DA）

Reverse Action（RA）（Air-to stem down）（Air-to stem up）

valve travel balancing between the force
on the diaphragm by the signal air pressure, and the spring force.
The Model 2800 diaphragm
actuators are designed for large output
thrust applying single-spring type, to bein-stalled on large size valve bodies.

1. SPECIFICATIONS

Output Thrust

Model 2800 Pneumatic single-acting spring diaphragm actuator
Direct action（DA）, Reverse action（RA）（mm）
N（kgf）

500S

500L

650S

650L

650XS

650XL

65

10065

13065

1309490（968）〔at off-balance 80kPaG（0.8kgf/cm2G）〕

With positioner
Without positioner
With positioner
Linearity
Without positioner
Diaphragm
Materials
Yoke
Supply Air Pressure kPaG（kgf/cm2G）
Hysteresis Error

Spring Range kPaG（kgf/cm2G）

16470（1680）

32950（3360）

Max. ± 1 % F.S.（2）Max. ± 4 % F.S.（2）Max. ± 1 % F.S.（2）Max. ± 5 % F.S.（2）Cloth reinforced chioroprene rubber（※ Ethylene propylene rubber）
FC200（※SCPH2）
120（1.2）, 240（2.4）, 280（2.8）,（120 only for 500 S ／ L）
20 〜 100（0.2 〜 1.0）
，40 〜 200
（0.4 〜 2.0）
，60 〜 220（0.6 〜 2.2）
，80 〜 240（0.8 〜 2.4），100 〜 220（1.0 〜 2.2〔）（20 〜 100 only for 500 S／L）〕

Air Connection
Ambient Temperature
Dimensions, Masses
Painting Color
Additional Mechanisms, Rc 3 ／ 8（650S, 650L, 650XS, 650XL）, ※ NPT
Rc 1 ／ 4（500S, 500L）

Options

Pneumatic positioner（IP300）, Electro-pneumatic positioner（EA91A, EA90A,EA10S）, Air filter regulator（MR2000）, Limit switch, Solenoid valve, Booster
relay, Speed controller, Lock up valve※Accessories− 30 ℃〜＋ 70 ℃（※− 50 ℃〜− 30 ℃, ＋ 70 ℃〜＋ 100 ℃）
See page 2 Table 1.
SilverTop-mounted handwheel, Side-mounted handwheel, Travel stop, Oil dash pot

2800

TypeAction
Actuator Sizes
Max Stroke【Note】（1）※ is available as option.
（2）Without positioner, the performance may vary in combination with valve type and gland packing.
（3）Material designation is represented by new JIS（SI Unit）. Please consent in advance that approval drawings and otherdocuments may Wrepresent with old material designation.

1Model 2800
Table 1. Dimensions and Weight

Unit : mmActuator Size

500S

500L

Effective Diaphragm Area（cm2）
Max. Diaphragm Chamber
Volume（cm3）1210

External Dimensions

650XS

2100

650XL
4200

10100

13500

16400

27600

16400

27600

RA

11500

16200

17800

29100

17800

29100

650

500

DA ; HD

734

820

1030

1133

1509

1744

RA ; HR

885

955

1270

1425

1803

2038

273

309

308

370

207

179

243

240

DA ; WDStem Length

650L

DA

Outside Dia.
of Diaphragm Casing φDHeight650S

265

RA ; WR200165

Threads of valve stem

W 3/4 10 threads

Yoke Insertion Dia.φY100

Yoke Thickness T

40

Yoke Mounted Thread Hole PCD φP

135160（mm） No. and Dia. of Yoke Mounted Thread Hole

6-φ196-φ23

170200

Yoke Spud Dia

φaApproximate Weight（kg）

W 7/8 9 threads

M30 × 2.01204360

DA

85

102270275

365395RA

100

120295300

395425Model 2800
650XS, 650XL

Model 2800
DARADARAφDφDφDφDHRHDHRHDaWD
WRTWDTWRTT

2. ADDITIONAL MECHANISMSφB

1 Top-mounted Handwheels（only for 500S, 500L DA）
Table 2. Dimensions and Weights for unit with Top-mounted Handwheel
500 SActuator Size

400Handwheel Dia. φ B
1159

1245

65

100

Turns for Max. Stroke

12.8

19.7

Approximate Weight（kg）

110

130

Max. Height

2800

500 L

HD

Max. Stroke

Unit ： mm

2HD

Model 2800
2 Side-mounted Handwheels
Table 3. Dimensions and Weight for unit with Side-mounted HandwheeldActuator Size
Handwheel Dia φ B
Handwheel Projection S
DA ; HD
HeightRA ; HR
Center -to-center distance M
Max. Stroke

500STurns for Max. Stroke

500L650S

300

650L

Unit : mm650XS

400

285

650XL
500

300

330

1113

1198

1140

1243

1722

1957

1180

1250

1380

1535

2016

2251

65

100

65

130

65

130

177.5

273

92.2

184.4

148

297

150（175）

315（330）320（350）415（440）450（485）

100

Approximate Weight（kg） 130（150）

115

204

【Note】Dimensions in parenthesis represent for Reverse Action（RA）.

500 SL DA

500 SL RA, 650 SL DA, RA

650X SL DA, RA【Note】※Marked dimension represents for actuator size 650.

3 Travel Stops-DD-Travel stops are usesd to limit the valve travel to certain
position for application purpose.

-RD-＜ Example ＞

HD

Actuator size 500 S, direct action, push-down close, tolimit full open

HR500S -D U - O
Direction for valve travel limit（O ： Open, S ： Shut）-DU--RU-

Direction for stem limit（U ： Upward, D ： Downward）
φB

Actuator action（D ： Direct action, R ： Reverse action）

HDActuator size

Table 4. Heights of Travel Stop and Classification

Direct Action（DA）
Reverse Action（RA）

Direction for
Stem Limit
Downward-DUpward

Symbol-DD-U-DU

Downward-D-RDUpward-U-RU

Direction forValve Travel LimitApplication

Shut-S

Limit for full shut ofpush-down close valve

Open-O

Limit for full shut ofpush-down open valve

Shut-S

Limit for full shut ofpush-down open valve

Open-O

Limit for full shut ofpush-down close valve

Shut-S

Limit for full shut ofpush-down close valve

Open-O

Limit for full shut ofpush-down close valve【Note】The stroke range of travel stop may be limitted by conditions in service.

Height500S

Actuator Size
500L 650S

650L

1031

1152

1443

1546

1031

1152

1443

1546

1164

−−−

1095

−−−

2800

Actuater Action

Unit : mmHDHR3

Model 2800
4 Oil Dash Pots（Dampers）

DA

Please inquire to use the oil dash pot under thefollowing conditons.
For single seated valve,fluid flows in direction to close the valve plug.
For double seated valve,（1）inlet pressure is high, and fluctuation ofl
differential pressure is large.
（2）Velocity of fluid is high.

RAOil dash pot

Oil dash pot

stop
valve
restrictor

stop
valve

restrictor

restrictor

Table 5. Dimensions for Oil Dash Pot
restrictor

Unit : mmActuator Size 500S 500L 650S 650L
Height DA ; HD（mm） RA ; HR1065

1220

1540

1645

1105

1300

1560

1715

3. POSITIONER MOUNTING DIMENSIONS
2 Electro-pneumatic Positioner EA91A, EA90A

1 Pneumatic Positioner IP300
Actuator

FlowDirection

Flow
Direction

Actuator
Actuator

Side-mounted
Handwheel

Table.6. Mounting Dimensions for IP300
500 L
Actuator Size 500 S
500Actuator outside Dia.φDDA RA DA RA
Action170
J270
KSide-mounted
Handwheel

Unit : mm Table.7. Mounting Dimensions for650 L

650 S

EA91A, EA90A

650DARADARA240270

2800【Note】The mounting dimensions for other positioner may be different from the above mentioned.

4Actuator

Unit : mm
SL650 SL

Actuator Size

500

Actuator outside Dia.φD500

650

J225300

K245

Bulletin No.MCE-B5101I

http://www.motoyama-cp.co.jp
本 社 工 場

Main Office & Factory

TEL（022）344-4511（代表） / FAX（022）344-4522
E-mail : info@motoyama-cp.co.jp
5-2, Ohira Aza Kameoka, Ohira-mura, Kurokawa-gun, Miyagi, 981-3697, Japan
TEL +81-22-344-4511 / FAX +81-22-344-4522
E-mail : info-overseas@motoyama-cp.co.jp〒981-3697 宮城県黒川郡大衡村大衡字亀岡５－２●販売・サービスネットワーク

東京支店〒210-0007 神奈川県川崎市川崎区駅前本町 10-5 クリエ川崎 11F

TEL（044）381-8770（代表） FAX（044）381-8772

大阪支店〒550-0014 大阪市西区北堀江 1 丁目 12-19 クリモトビル 3F

TEL（06）6535-8111（代表） FAX（06）6535-8655

国際営業部〒210-0007 神奈川県川崎市川崎区駅前本町 10-5 クリエ川崎 11F

TEL（044）381-8771

FAX（044）381-8773

札幌営

業所

〒001-0912 札幌市北区新琴似12条7丁目1-47
リバティタウンP棟101号

TEL（011）766-1520

FAX（011）766-1521

東

北営

業所

〒981-3697 宮城県黒川郡大衡村大衡字亀岡 5-2

TEL（022）344-1761

FAX（022）344-1762〒942-0036 新潟県上越市大字東中島2393番地

TEL（025）542-5151

FAX（025）542-5152〒290-0046 千葉県市原市岩崎西1丁目5-19

TEL（0436）21-4400

FAX（0436）21-3540〒422-8033 静岡市駿河区登呂4丁目28-5

TEL（054）269-5377

FAX（054）237-5855〒481-0012 愛知県北名古屋市久地野安田36番地

TEL（0568）26-6681

FAX（0568）26-6631〒710-0042 岡山県倉敷市二日市358

TEL(086)486-3381

FAX(086)486-3382

阪 神 サー ビ スセンター〒560-0894 大阪府豊中市勝部2丁目18-3

TEL（06）6854-7511

FAX（06）6854-7512

姫路

出張所

〒672-8014 兵庫県姫路市東山276番地1

TEL（079）263-8640

FAX（079）246-2130

徳山営

業所

〒745-0861 山口県周南市新地1丁目6-11

TEL（0834）21-5012

FAX（0834）31-0450〒792-0896 愛媛県新居浜市阿島1丁目6-26

TEL（0897）47-8993

FAX（0897）47-8995〒870-0108 大分市大字三佐字山ノ神980-1

TEL（097）527-3704

FAX（097）522-2352

TEL +86-411-6589-1277

FAX +86-411-6589-1278

大 衡 サービスセンター

上越営

業所

上 越 サービスセンター

関東営

業所

千 葉 サービスセンター

静岡営

業所

名 古 屋 営 業 所
中 部 サービスセンター

水島営

業所

周 南 サービスセンター

四国営

業所

新 居 浜 サービスセンター

大分営

業所

大 分 サービスセンター●海外関連会社本山阀门（大連）有限公司 〒116601 中国 遼寧省大連市金州新区港興大街 39 号 14-7
●海外販売代理店

中国、韓国、台湾、シンガポール、インドネシア、マレーシア、サウジアラビア●SALES AND SUPPORT NETWORK

Overseas Marketing & Sales Dept. : 11th Floor, Clie Kawasaki, 10-5, Ekimae-honcho, Kawasaki-ku, Kawasaki-city, Kanagawa, 210-0007 Japan
TEL: +81-44-381-8771
FAX : +81-44-381-8773
Domestic Sales Branches : Tokyo, Osaka, Sapporo, Tohoku, Joetsu, Kanto, Shizuoka, Nagoya, Hanshin, Tokuyama, Shikoku, Oita

●OVERSEAS AFFILIATED COMPANY

MOTOYAMA VALVE （DALIAN） CO., LTD
Gangxing Street 39-14-7, Jinzhou New District, Dalian-city, 116601 China

TEL: +86-411-6589-1277

FAX: +86-411-6589-1278●OVERSEAS NETWORK

China, Korea, Taiwan, Singapore, Indonesia, Malaysia, Saudi Arabia◆当社は保証期間を原則として製品納入後１年としています。
◆The product will be warranted for one year after delivering this product in principle.
■本カタログの記載内容は、商品の改良等のため予告なく変更することがありますので予めご了承下さい。
■MOTOYAMA is continuously improving and upgrading its product design, specifications and/or dimensions. Information included herein issubject to change without notice.

■本カタログは正しい情報の提供を目的としたものであり、本製品の市場性または適合性の保証を証明するものではありません。
■This catalog is supplied for information purpose only and should not be considered certified marketability and conformability of thisproduct.

202402 MSP