ATEX Compliant

Pressure Switch/Reed Switch Type

Series 56-IS10
II 3G Ex h ec IIB T5Gc
-5°C ≤ Ta ≤ +60°C
II 3D Ex h tc IIIB T90°C Dc

How to Order

56 IS1001q

ATEX category 3
qw
SymbolDescription

Thread type

NilN

NPT

Seal

NilS+

w

+

Semi-standardae

Set pressurerange

Lead wire
lengthb3m

Example) 56-IS10-N01-6PZ

5m

Scale platepressure unit

Note 1) Set pressure range of6P(L, Z) is 0.2 to 0.6
MPa (30 to 90 psi).
Note 2) This product is for overseas use only according to the new Measurement Law. (The SI
unit type is provided foruse in Japan.)

NilMPaP Note1) Both MPa and psi

Max. contact capacity
Voltage AC/DC

0.7 MPa

Set pressure range

0.1 to 0.4 MPa
Option: 0.1 to 0.6 MPa

Ambient and fluid temperature–5 to 60°C (No freezing)

Max. operating current

AC 2 VA, DC 2 W
24 V or less
48 V
50 mA

40 mA

1aError of scale±0.05 MPa or less

Hysteresis

Fixed 0.08 MPa or less

EnclosureSemi-standard: Select one
option each in a through c.
Place them in alphanumericalorder.

0.5 m

Air/Inert gas
1.0 MPa

Wiring specifications

NilLZ56-IS10-01

Max. operating pressure

Repeatability

0.1 to 0.4 MPa

6 Note1) 0.1 to 0.6 MPa

Switch Characteristics

Proof pressure

Contacts

None
With seal+Specifications
ModelNil

R+c

Fluide±0.05 MPa or less
Grommet, Lead wire length: 0.5 m
Option: 3 m, 5 m
Equivalent to IP40

Port size

1/8

Weight62 gAll other specifications are the same as thestandard products Series IS10.
Click here for details.

98-1 A

Series 56-IS10
Pressure Switch for Series AC-D
Pressure Switch

56 IS10M 30q

ATEX category 3DBody type: Standard(56-IS10M-mm-D)

Body type: Slim
(56-IS10M-mm-1-D)w· Semi-standard: Select one each for a to d.
· Semi-standard symbol: When more than one specification is required, indicate in alphanumeric order.
Example) 56-IS10M-30-6LP-Dq

SymbolBody size[Applicable AC size]

Description

2030

405060Assembly Examples

Pressure switch[AC20] [AC30] [AC40] [AC40-06] [AC50, AC60]
Set pressurerange

Nil
6*10.1 to 0.4 MPa
0.1 to 0.6 MPa

v

vv

v


v

b

Lead wirelengthNilL
Z

0.5 m3m5mcPressure unit ofthe scale plate

NilP*2MPaMPa/psi dual scalev

v

v

v

v

Body type

Nil
1StandardSlim




w


Semi-standarda++d+: Without restrictions
v: With restrictions (Refer to *1 and *2.)

*1 The set pressure range for the 6P is 0.2 to 0.6 MPa (30 to 90 psi).
*2 This product is for overseas use only according to the New Measurement Act.
(The SI unit type is provided for use in Japan.)Caution on Mounting
Pipe threads are not provided on the face which connects with the other components. For use, a separate spacer (or spacer with bracket)
is required.

B

98-2

ATEX Compliant Pressure Switch/

Reed Switch Type Series

56-IS10

Pressure Switch for Series AC-D
Pressure Switch with T-Spacer

56 IS10T 30
ATEX category 3q03
w

e

Dr

· Semi-standard: Select one each for a to c.
· Semi-standard symbol: When more than one specification is required, indicate in alphanumeric order.
Example) 56-IS10T-30-N03-6LP-DINq


OUT q(Port size)

Body size[Applicable AC size]

Symbol Description

2030405060

INOUT
OUT q

[AC20] [AC30] [AC40] [AC40-06] [AC50, AC60]

NilN
FRc
NPTG











Port size(OUTq)

01
02
03
04
06

1/8
1/4
3/8
1/2
3/4

———



———

——




——



Set pressurearangeNil
6*1

0.1 to 0.4 MPa
0.1 to 0.6 MPa

v

v

v

v

v

Leadwirelength

NilLZ

0.5 m
3m5m




v


v

v


v

v

w
 Pipe thread type+er

Semi-standard+b

Pressure unit ofc
the scale plate++

MPa
Nil
P*2 MPa/psi dual scale

OUT

Port size——eAssembly
ExamplesPressure switch with T-spacer

: Without restrictions
v: With restrictions (Refer to *1 and *2.)

*1 The set pressure range for the 6P is 0.2 to 0.6 MPa (30 to 90 psi).
*2 For the pipe thread type: NPT onlyThis product is for overseas use only according to the New Measurement Act.
(The SI unit type is provided for use in Japan.)Caution on Mounting· Pipe threads are not provided on the face which connects with the other components. For use, a separate spacer (or spacer withbracket) is required.
· The backflow of oil may occur when a spacer is used on the inlet side of the lubricator. Attach a check valve between the lubricator andthe product to prevent backflow.

98-3 BSeries 56-IS10
Pressure Switch for Series AC-D
Pressure Switch with L-Shaped Piping Adapter

56 IS10L 30
ATEX category 3q03w

eDr· Semi-standard: Select one each for a to d.
· Semi-standard symbol: When more than one specification is required, indicate in alphanumeric order.
Example) 56-IS10L-30-N03-6LP-D

INq

OUT
(Port size)

Body size[Applicable AC size]

Symbol Description

2030

40

5060

IN
OUT

[AC20] [AC30] [AC40] [AC40-06] [AC50, AC60]w
 Pipe thread typeNilN
F

RcNPTG

0102
030406
10

1/8
1/4
3/8
1/2
3/41
————————
—————

————



+Port size(OUT)er

Semi-standard+a

Set pressurerange

Nil
6*1

0.1 to 0.4 MPa
0.1 to 0.6 MPa

v

v

v

v

v

b

Leadwire
length

NilL
Z

0.5 m
3m5m



















++Pressure unit ofc
the scale plateMPa
Nil
P*2 MPa/psi dual scale

v

v

v

v

v

Mountingdposition

NilR








+RightLeft

Port size—eAssembly Examples

Left

Right
Pressure switch
with L-shaped
piping adapter

: Without restrictions
v: With restrictions (Refer to *1 and *2.)

*1 The set pressure range for the 6P is 0.2 to 0.6 MPa (30 to 90 psi).
*2 For the pipe thread type: NPT onlyThis product is for overseas use only according to the New Measurement Act.
(The SI unit type is provided for use in Japan.)Caution on Mounting
Pipe threads are not provided on the face which connects with the other components. For use, a separate spacer (or spacer with bracket)
is required.

B98-4ATEX Compliant Pressure Switch/Reed Switch Type Series

56-IS10

Pressure Switch for Series AC-D
Pressure Switch with Piping Adapter

56 IS10E 30
ATEX category 3q03w

eDr· Semi-standard: Select one each for a to d.
· Semi-standard symbol: When more than one specification is required, indicate in alphanumeric order.
Example) 56-IS10E-30-N03-6LP-D

IN

OUT(Port size)qBody size[Applicable AC size]

Symbol Description

2030

405060IN
OUT

Port size—e[AC20] [AC30] [AC40] [AC40-06] [AC50, AC60]w
 Pipe thread typeNilNFRcNPTG

01
02
03
04
06
10

1/8
1/4
3/8
1/2
3/41

————


———


—————


————


+Port size
(OUT)

er


Semi-standard+a

Set pressure
range

Nil
6*1

0.1 to 0.4 MPa
0.1 to 0.6 MPa

v

v

v

v

v

b

Leadwire
length

NilLZ

0.5 m
3m5m



MPa
Nil
P*2 MPa/psi dual scalevv


v

v

v

NilR











Pressure unit ofc
the scale platedMounting
position+++

Right
Left

Assembly Examples

Left

Right
Pressure switch withpiping adapter

: Without restrictions
v: With restrictions (Refer to *1 and *2.)

*1 The set pressure range for the 6P is 0.2 to 0.6 MPa (30 to 90 psi).
*2 For the pipe thread type: NPT onlyThis product is for overseas use only according to the New Measurement Act.
(The SI unit type is provided for use in Japan.)Caution on Mounting
Pipe threads are not provided on the face which connects with the other components. For use, a separate spacer (or spacer with bracket)
is required.

98-5 B