ATEX Compliant

Fieldbus System

56-EX600 Series
How to Order

SI Unit

56-EX600 S PN1 X10Protocol
SymbolPR1A
PN1

Description
PROFIBUS DPPROFINETII 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C
II 3D Ex tc IIIC T82°C Dc IP67

Digital Input Unit

56-EX600 DX P D X10
Input type PNP

Number of Inputs, Open circuit detection, and Connector
Symbol Number of inputs Open circuit detectionNo
B 8 inputs
No
C 8 inputs
No
D 16 inputs

Connector
M12 connector (5 pins) 4 pcs.
M8 connector (3 pins) 8 pcs.
M12 connector (5 pins) 8 pcs.

II 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C (56-EX600-DXPB-X10)
II 3D Ex tc IIIC T82°C Dc IP67
(56-EX600-DXPC-X10)
II 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C
(56-EX600-DXPD-X10)
II 3D Ex tc IIIC T86°C Dc IP67

Digital Output Unit

56-EX600 DY P B X10
Output type PNP

Number of Outputs and Connector
Symbol Number of outputs
Connector
8 outputs
M12 connector (5 pins) 4 pcs.
B

II 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C
II 3D Ex tc IIIC T68°C Dc IP67

Analog Input Unit

56-EX600 AX A X10Analog input

Number of Input channels and Connector
Symbol Number of input channelsConnector
2 channels
M12 connector (5 pins) 2 pcs.
A

II 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C
II 3D Ex tc IIIC T66°C Dc IP67

D257

ATEX Compliant

Fieldbus System

56-EX600 Series

How to Order

Analog input/output

2 channels

2 channels

Connector
M12 connector (5 pins)
4 pcs.

End plate
End plate mounting position: D side
Power supply connector
Symbol Power supply connector SpecificationsM12 (5 pins) B-coded
IN2
7/8 inch (5 pins)
IN
3Nil

Description
Without DIN rail
mounting bracket

2With DIN rail
mounting bracket

II 3G Ex ec IIC T4 Gc -10°C≤ Ta ≤50°C(56-EX600-ED2-X10)
II 3D Ex tc IIIC T72°C Dc IP67

EX250
Note
—
For SV, S0700, VQC series

EX180

II 3G Ex ec IIC T4 Gc -10°C≤ Ta ≤50°C(56-EX600-ED3-X10)
II 3D Ex tc IIIC T77°C Dc IP67

M8/M12For 7/8 inch

Mounting methodSymbol

ATEX

For M122 X10Type 156-EX600 E D 2Type 2End Plate

Type 3

II 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C
II 3D Ex tc IIIC T76°C Dc IP67

EX120/121/122

BEX600

Number of Input/Output channels and Connector
Symbol Number of input channels Number of output channels

EX245

AM B X10EX140

Analog Input/Output Unit 56-EX600

Type 2

II 3G Ex ec IIC T4 Gc -10°C ≤ Ta ≤ 50°C
II 3D Ex tc IIIC T67°C Dc IP67

EX123/124/126

Connector
M12 connector (5 pins) 2 pcs.

EX500

Number of Output channels and Connector
Symbol Number of output channels
2 channels
AEX510

Analog output

EX260

AY A X10Type 1

Analog Output Unit 56-EX600

257-1 BATEX Compliant

Fieldbus System

56-EX600 SeriesSpecifications

PROFIBUS DP (DP-V0)
PROFIBUS DP Slave
9.6/19.2/45.45/93.75/187.5/500 kbps 1.5/3/6/12 Mbps
GSD file
Type 2Max. (512 inputs/512 outputs)
Internally implemented
Source/PNP (Negative common)
32 outputs (8/16/24/32 outputs selectable)
Solenoid valve with surge voltage suppressor 24 VDC, 1.5 W or less (SMC)
24 VDC, 2 A
HOLD/CLEAR/Forced power ON
Short-circuit protection
IP67 (Manifold assembly)
300 g

SI Unit
56-EX600-SPN1-X10

Max. (512 inputs/512 outputs)
120 mA or less
Source/PNP (Negative common)
32 outputs
Solenoid valve with surge voltage suppressor 24 VDC, 1.0 W or less (SMC)
24 VDC, 2 A
HOLD/CLEAR/Forced power ON
Short-circuit protection
IP67 (Manifold assembly)
300 g

Digital Input Unit

M12 (5-pin) socket∗10.25 A/Connector
2 A/Unit

0.5 A/Connector
2 A/Unit

Short-circuit protection

Input current (at 24 VDC)

9 mA or lessON voltage

17 V or more (At NPN input, between the pin for input terminal and supplied voltage of +24 V)(At PNP input, between the pin for input terminal and supplied voltage of 0 V)

OFF voltage

5 V or less (At NPN input, between the pin for input terminal and supplied voltage of +24 V)(At PNP input, between the pin for input terminal and supplied voltage of 0 V)
50 mA or less

Enclosure
Weight

55 mA or less

70 mA or less

EX510

Input

M8 (3-pin) socket∗224 VDC

0.5 A/Connector
2 A/Unit

Protection

Current consumption

EX180

M12 (5-pin) socket∗18 inputs (2 inputs/Connector) 8 inputs (1 input/Connector) 16 inputs (2 inputs/Connector)

Supplied voltage
Max. supplied current

56-EX600-DXPD-X10

PNP

M8/M12

Number of inputs

56-EX600-DXPC-X10

IP67 (Manifold assembly)
300 g

275 g

340 g

∗1 M12 (4-pin) connector can be connected.
∗2 When connecting the M8 plug connector, the tightening torque must be 0.2 N·m ±10%. If tightened with anexcessive tightening torque, this may cause the connector thread of the unit to break.

56-EX600-DXPD-X10

258 AATEX

Input connector

56-EX600-DXPB-X10Type 2Model
Input type

56-EX600-DXPC-X10

EX120/121/122

Output56-EX600-DXPB-X10

EX250

PROFINET IO (PROFINET RT)
100 Mbps
GSDML file

Communication

ModelProtocol
Communication speed
Configuration file
Occupation area
(Number of inputs/outputs)
Internal current consumption(Power supply for Control/Input)
Output type
Number of outputs
LoadPower supply
Fail safe
Protection
Enclosure
Weight

EX600

80 mA or less

EX123/124/126

56-EX600-SPR1A-X10

EX140

OutputCommunication

Model
ProtocolDevice typeCommunication speed
Configuration file
Occupation area
(Number of inputs/outputs)
Terminating resistor
Internal current consumption(Power supply for Control/Input)
Output type
Number of outputs
LoadPower supply
Fail safe
Protection
Enclosure
WeightEX245

SI Unit

EX500

Type 1EX260–10 to 50°C
–20 to 60°C
35 to 85%RH (No condensation)
500 VAC for 1 minute between external terminals and FE
500 VDC, 10 MW or more between external terminals and FE

Type 3Operating temperature range
Storage temperature range
Operating humidity range
Withstand voltage
Insulation resistanceType 1

Environmental resistance

All Units Common Specifications

56-EX600 SeriesSpecifications
Digital Output Unit56-EX600-DYPB-X10

OutputModel
Output typeOutput connector

PNP
M12 (5-pin) socket*1

Number of outputs

8 outputs (2 outputs/Connector)

Supplied voltage

24 VDC

Max. load current

0.5 A/Connector
2 A/Unit

Protection

56-EX600-DYPB-X10

Short-circuit protection

Current consumption

50 mA or less

Enclosure

IP67 (Manifold assembly)

Weight

300 g*1 M12 (4-pin) connector can be connected.

Analog Input Unit
Model
Input type

56-EX600-AXA-X10
Voltage input

Current input

Input connector

M12 (5-pin) socket*1

Input channel

2 channels (1 channel/Connector)

Supplied voltage

24 VDC

56-EX600-AXA-X10Input

Max. supplied current

0.5 A/Connector

Protection

Short-circuit protection

12 bit resolution
Inputsignal range 16 bit resolution

0 to 10 V, 1 to 5 V, 0 to 5 V

0 to 20 mA, 4 to 20 mA–10 to 10 V, –5 to 5 V

Max. rated input signal±15 V
100 kW–20 to 20 mA±22 mA*2

Input impedance

50 W±0.05% F.S.

Linearity (25°C)±0.15% F.S.

Repeatability (25°C)
Absolute accuracy (25°C)±0.5% F.S.

±0.6% F.S.

Current consumption

70 mA or less

Enclosure

IP67 (Manifold assembly)

Weight290 g*1 M12 (4-pin) connector can be connected.
*2 When input signal exceeds 22 mA, the protection function activates and the input signal is interrupted.

Analog Output Unit

56-EX600-AYA-X10

OutputModel
Output type

56-EX600-AYA-X10
Voltage output
M12 (5-pin) socket*1

Output channel

2 channels (1 channel/Connector)

Supplied voltage

24 VDC

Max. load current

0.5 A/Connector

ProtectionOutput
12 bit resolution
signal range
Load impedance

Short-circuit protection
0 to 10 V, 1 to 5 V, 0 to 5 V±0.15% F.S.
±0.5% F.S.

Current consumption
Enclosure
Weight*1 M12 (4-pin) connector can be connected.

259

600 W or less±0.05% F.S.

Repeatability (25°C)
Absolute accuracy (25°C)

0 to 20 mA, 4 to 20 mA

1 kW or more

Linearity (25°C)

B

Current output

Output connector±0.6% F.S.
70 mA or less
IP67 (Manifold assembly)
290 g

ATEX Compliant

Fieldbus System

56-EX600 SeriesSpecifications
Analog Input/Output Unit
56-EX600-AMB-X10
M12 (5-pin) socket*1

Input channel

2 channels (1 channel/Connector)

Supplied voltage
Protection

Short-circuit protection

12 bitInput
signal range resolution

0 to 10 V, 1 to 5 V, 0 to 5 V

0 to 20 mA, 4 to 20 mA

Max. rated input signal

15 V

22 mA*2

Input impedance

100 kW

250 W
Type 2±0.05% F.S.
±0.15% F.S.

Repeatability (25°C)
Output type±0.6% F.S.
Current output

Output connector

M12 (5-pin) socket*1

Output channel

2 channels (1 channel/Connector)

Supplied voltage

24 VDC

Max. load current

0.5 A/Connector

Protection

EX600±0.5% F.S.
Voltage output

Absolute accuracy (25°C)

0 to 10 V, 1 to 5 V, 0 to 5 V

600 W or less

1 kW or more
±0.05% F.S.

Linearity (25°C)±0.15% F.S.

Repeatability (25°C)±0.5% F.S.

±0.6% F.S.

Current consumption
Enclosure

EX250

Absolute accuracy (25°C)

100 mA or less
IP67 (Manifold assembly)

Weight300 g

EX120/121/122*1 M12 (4-pin) connector can be connected.
*2 When input signal exceeds 22 mA, the protection function activates and the input signal is interrupted.

End PlateRated
voltageRatedcurrent

56-EX600-ED2--X10

56-EX600-ED3--X10

M12 (5-pin) plug

7/8 inch (5-pin) plug

—24 VDC ±10%Power supply for output

24 VDC +10/–5%Power supply for control/input
Power supply for output

Max. 2 A

Enclosure
Weight—Power supply for control/input

Max. 8 A

EX180

Power specifications

Model
Power supply PWR IN
connector
PWR OUT

Type 156-EX600-ED3-m-X10

IP67 (Manifold assembly)
170 g

EX140

Load impedance

0 to 20 mA, 4 to 20 mA

EX245

Short-circuit protection

12 bitOutput
signal range resolution

Type 3Input

0.5 A/Connector

Linearity (25°C)

OutputType 1

24 VDC

Max. supplied current

56-EX600-AMB-X10

EX260

Current input

Input connector

EX123/124/126

Voltage input

EX500

ModelInput type

175 g

EX510
ATEX

M8/M12Type 256-EX600-ED2-m-X10

259-1 B