RST® CLASSIC

Overview matrix RST® CLASSIC.
Codings and applications at a glance

Pole marking
Application

RST 20i2

RST 20i3

RST 25i32-pole, 20A

3-pole, 20A

3-pole,
32A

L, N

+, –

1, 2

L, N, 1, 2, 1, 2, 3

1, 2, L, N, 250V
black or lightgray~50/-120V
pebble gray~50/-120V
signal brown

250V
black or lightgray

250/400V
leaf green

250/400V
light blue

~50/-120V
signal brown

250V
concrete gray

S

F
S

F
S

F
S

F
S

S

Contact insert
male and female
Spring clamp (F)Screw (S)
Crimp (C)F
S

Distrib.
units

1 x cable entry

Ø 10 –14 mm

Flat cable
13 x 6 mm
AS-i
profile cableØ 6 –10 mm
Ø 10 –14 mm
AS-i
profile cable
M25
M16
straight
M16
7° angled
M20
straight
M20
angledM25
angledDistribution block1 I/3 ORST® compact/
multi-distribution units
Individual
distribution box

Cable
assemblies

Expansion cable
Female – MalePower connection
Female – Free end
Power connection
Male – Free end
Power connection
Safety plug – female
Power cable/contour cable
European connector, SKII – female

72

ü
ü

ü
ü

ü
ü

ü
ü
ü

ü
ü
ü

ü
ü
ü

ü
ü

ü
ü

ü
ü

ü
ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü

Ø 13 –18 mm

1
2 x cable entrypiece
2 piece

Device connectors

Connectors

Ø 6 –10 mm

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

F
S
C

ü
ü
ü
ü
ü

ü
ü

ü
ü
ü
ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

RST® CLASSIC

RST 20i4

RST 20i5

RST 25i5 RST 20i6

4-pole, 20A

5-pole, 20A

5-pole,25 A (3~)

RST 20i76-pole7-pole1,2,3,4/N,5,6,
1,2,3,4/N,5,6,7 L,N,,1,2,3,4


1, 2, 3, 

1, 2, 3, 4

1, 2, 3, N, 

L,N,,D1,D2

1, 2, 3, 4, 5

N, E, 1, 2, 3

1, 2, 3, 4, 5

L, N, , 1, 2

L,N,,1,2,LS

250/400V
black or lightgray~50/-120V
signal brown

250/400V
black or light
gray

250V
turquoise

250/400V
light blue

250/400V
yellow~50/-120V
signal brown

250/400V
concrete gray

250/400V
türkisblau

250/400V
black or lightgray

250/400V
light blue

250/400V
turquoise

S
C

S
C

S
C

S
C

S
C

S

S
C

S

S
C

S
C

S
C

S
C

ü

ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü

ü
ü
ü

ü
ü
ü

ü
ü
ü

ü
ü

ü
ü

ü
ü

ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü

ü
ü
ü

ü
ü

ü
ü

ü
ü

ü
ü

ü
ü
RST® CLASSIC

ü
ü
ü

ü
ü
ü

ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü
ü

ü
ü
ü
ü

ü
ü
ü
ü

ü
ü
ü
ü

ü
ü
ü
ü

73

RST 20i2

74

RST 20i2

Applications in the range of protection class II and
extra-low voltage for industry and LED technology

Application example

General

You therefore have the security of a clear separation of different
applications without having to redo any incorrect connections.
The color of the connectors indicates the links that belong
together.

RST® CLASSIC

The two-pole connectors are based on
the 3-pole variant, but with one pole
not configured.
There are essentially two variants.
One coding can be used for protection
class II applications and is downwardly
compatible with the 3-pole systemwith ground conductor (RST 20i3).
This makes it possible to transition
from a system with earthing contact
to a 2-pole system – but not the otherway round!
The other version is aimed atapplications in the extra-low voltage
range, such as serial or parallel LED
wiring, or at industrial applications
with 24 V auxiliary power and AS-i.
All connectors are mechanically coded.
This means that only associated pairsof male and female can be connectedwith the correct polarity.

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

Name
Connector

Distribution
units

Deviceconnectors

Cable
assemblies

Description
1 x cable entry
2 x cable entry
Distribution block1 I/3 O
RST compact distribution
unit/multi-distribution unit

Connection
style
Screw
Spring clamp
Screw
Spring clamp

Round cableAS-i profile cable~50/-120V

L, N

+, -

1, 2

pebblegraysignalbrown

MechanicalcodingStrain relief
housingyes
yesConnection points
per pole
12
12

light grayblack

ü ü ü üü ü ü üü ü ü üü üüüü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü
on request

onrequestIndividual distribution box
Series distribution unit
for power LEDs
M16 device connector,
modular, straightM16 device connector,
modular, angled 7°
M25 device connector,
standard
M20 device connector,
standard
M20 device connector,
modular, straightM25 device connector,
modular, angled
Connection cableMale – Free end
Connection cable
Female – Free end
Connection cableMale – Female
Connection cable
Europ. conn. SK II – Female

250V

preassembled
preassembled
preassembled
preassembled
preassembled
preassembled

preassembled
preassembled
preassembled
preassembled
preassembled
preassembled

preassembled
preassembled
preassembled
preassembled
preassembled
preassembled

onrequeston request

onrequest75

RST 20i2

Connectors, straightfor cables Ø 6 – 10 mm and 10 –14 mm

Female connector
Unmounted with cable gland.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingCable diameter in mm

6 – 10
10 – 14

L, N

250V

1, 2
+, –

~50/-120V
1, 2

Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52
6 – 10
10 – 14
Round cable 6 –10
AS-i profile cable
6 – 10AS-i profile cable
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

mm2

fine-stranded

0.5 – 1.5

fine-stranded

0.75 – 6.02)

stranded

0.75 – 1.5

Color

FerruleswithferruleswithferrulesstrandedPart No.

Part No.

light grayblack
light grayblack
light grayblack
leaf green
leaf green
pebble graypebble graysignal brownsignal brown

96.021.0053.0
96.021.0053.1
96.021.0153.0
96.021.0153.1
96.021.0453.0
96.021.0453.1
on request
on request
96.021.0050.8
96.021.0950.8
96.021.0051.4
96.021.0951.4

96.021.4053.0
96.021.4053.1
96.021.4153.0
96.021.4153.1
96.021.4453.0
96.021.4453.1
96.021.4055.7
96.021.4155.7
96.021.4050.8
96.021.4950.8
96.021.4051.4
96.021.4951.4

signal brown

96.021.0451.4

96.021.4451.4

without
ferruleswithout
ferrulesMale connector
Unmounted with cable gland and locking
device.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingCable diameter in mm

6 – 10
N, L

250V
1, 2
–, +

~50/-120V
2, 1

10 – 14
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52
6 – 10
10 – 14
Round cable 6 –10
AS-i profile cable
6 – 10AS-i profile cable
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52

Colorwith spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

mm2

fine-stranded

0.5 – 1.5

fine-stranded

0.75 – 6.02)

stranded

0.75 – 1.5

FerruleswithferruleswithferrulesPart No.

Part No.

light grayblack
light grayblack
light grayblack
leaf green
leaf green
pebble graypebble graysignal brownsignal brown

96.022.0053.0
96.022.0053.1
96.022.0153.0
96.022.0153.1
96.022.0453.0
96.022.0453.1
on request
on request
96.022.0050.8
96.022.0950.8
96.022.0051.4
96.022.0951.4

96.022.4053.0
96.022.4053.1
96.022.4153.0
96.022.4153.1
96.022.4453.0
96.022.4453.1
96.022.4055.7
96.022.4155.7
96.022.4050.8
96.022.4950.8
96.022.4051.4
96.022.4951.4

signal brown

96.022.0451.4

96.022.4451.4

With wire protection available on request
With 6.0 mm2 wires, the pull and bending forces at the connector must be taken into consideration and compensated using suitable measures if required.
See also chapter on Technical Data and eShop.
1)
2)

76

stranded

without
ferruleswithout
ferrulesRST 20i2

Connectors, angled 90°

for cables Ø 6 – 10 mm and 10 –14 mm

Female connector
Unmounted with cable gland.
90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

CodingCable diameter in mm

6 – 10250V

10 – 14

L, N

+, –

~50/-120V
1, 2

Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52
Round cable 6 –10
AS-i profile cable
6 – 10AS-i profile cable
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

mm2

fine-stranded

0.5 – 1.5

fine-stranded

0.75 – 6.02)

stranded

0.75 – 1.5

Color

FerruleswithferruleswithferrulesstrandedPart No.

Part No.

light grayblack
light grayblack
light grayblack
pebble graypebble graysignal brownsignal brown

96.023.0053.0
96.023.0053.1
96.023.0153.0
96.023.0153.1
96.023.0453.0
96.023.0453.1
96.023.0050.8
96.023.0950.8
96.023.0051.4
96.023.0951.4

96.023.4053.0
96.023.4053.1
96.023.4153.0
96.023.4153.1
96.023.4453.0
96.023.4453.1
96.023.4050.8
96.023.4950.8
96.023.4051.4
96.023.4951.4

signal brown

96.023.0451.4

96.023.4451.4

without
ferruleswithout
ferrules

RST® CLASSIC

Application

with spring clamp connection

Male connector
Unmounted with cable gland.
90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingCable diameter in mm

6 – 10
250V

N, L

–, +

~50/-120V
2, 1

10 – 14
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52
Round cable 6 –10
AS-i profile cable
6 – 10AS-i profile cable
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52

Colorwith spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

mm2

fine-stranded

0.5 – 1.5

fine-stranded

0.75 – 6.02)

stranded

0.75 – 1.5

FerruleswithferruleswithferrulesstrandedPart No.

Part No.

light grayblack
light grayblack
light grayblack
pebble graypebble graysignal brownsignal brown

96.024.0053.0
96.024.0053.1
96.024.0153.0
96.024.0153.1
96.024.0453.0
96.024.0453.1
96.024.0050.8
96.024.0950.8
96.024.0051.4
96.024.0951.4

96.024.4053.0
96.024.4053.1
96.024.4153.0
96.024.4153.1
96.024.4453.0
96.024.4453.1
96.024.4050.8
96.024.4950.8
96.024.4051.4
96.024.4951.4

signal brown

96.024.0451.4

96.024.4451.4

without
ferruleswithout
ferrulesWith wire protection available on request
With 6.0 mm2 wires, the pull and bending forces at the connector must be taken into consideration and compensated using suitable measures if required.
See also chapter on Technical Data and eShop.
1)
2)

77

RST 20i2

Splitter connector, straightfor cables Ø 6 – 10 mm and 10 –14 mm

Female connector
Unmounted with cable gland.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingCable diameter in mm

6 – 10250V~50/-120V

L, N

1, 2

10 – 14
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52
6 – 10AS-i profile cable
Illumination cable 13.3x5.3
H05RNH2-F2 x 1.52

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

mm2

fine-stranded

0.5 – 1.5

fine-stranded

0.75 – 2.5

stranded

0.75 – 1.5

Color

Ferruleswithferruleswithferruleswithout
ferruleswithout
ferrulesstrandedPart No.

Part No.

light grayblack
light grayblack
light grayblack
signal brownsignal brown

96.021.0253.0
96.021.0253.1
96.021.0353.0
96.021.0353.1
on request
on request
96.021.0251.4
96.021.0351.4

96.021.4253.0
96.021.4253.1
96.021.4353.0
96.021.4353.1
on request
on request
96.021.4251.4
96.021.4351.4

signal brown

on request

on request

Mounting plate for splitter connectors
Colorn grayn black

1)

78With wire protection available on request

Part No.
01.006.1553.0
01.006.1553.1

RST 20i2

M25 device connector
straight, standard

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from outside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.
For spacer rings for unlocking at the device
connetor, see Accessories.

Coding

250V

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M25 x 1.5
outside

Color
L, N
+, –

~50/-120V

with screw connection1)

1, 2

Ferruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M25 x 1.5
outsidePart No.

Part No.

light grayblack
pebble gray96.021.1053.0
96.021.1053.1
96.021.1050.8

96.021.5053.0
96.021.5053.1
96.021.5050.8

signal brown

96.021.1051.4

96.021.5051.4

without
ferruleswithout
ferrules

RST® CLASSIC

Application

with spring clamp connection

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from outside.
With locking device.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

250V

Coding

Color
N, L
–, +

~50/-120V
1, 2

1)

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M25 x 1.5
outsideFerruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.02)

strandedTerm. poles
ThreadGland1
M25 x 1.5
outsidePart No.

Part No.

light grayblack
pebble gray96.022.1053.0
96.022.1053.1
96.022.1050.8

96.022.5053.0
96.022.5053.1
96.022.5058.8

signal brown

96.022.1051.4

96.022.5051.4

without
ferruleswithout
ferrulesWith wire protection available on request

79

RST 20i2

M16 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

Coding250Vwith spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M16 x 1.5
inside

Color

L, N
+, –

~50/-120V
1, 2

Ferruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M16 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.021.2153.0
96.021.2153.1
96.021.2150.8

96.021.6153.0
96.021.6153.1
96.021.6150.8

signal brown

96.021.2151.4

96.021.6151.4

without
ferruleswithout
ferrulesMale connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip lengths
as well as the ferrules to be used.

Application

250V

Coding

Color
N, L
–, +

~50/-120V
1, 2

1)

80

With wire protection available on request

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M16 x 1.5
insideFerruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M16 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.022.2153.0
96.022.2153.1
96.022.2150.8

96.022.6153.0
96.022.6153.1
96.022.6150.8

signal brown

96.022.2151.4

96.022.6151.4

without
ferruleswithout
ferrulesRST 20i2

M16 device connector
angled 7°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Coding250Vwith screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M16 x 1.5
inside

Color

L, N
+, –

~50/-120V
1, 2

Ferruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M16 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.025.2153.0
96.025.2153.1

96.025.6153.0
96.025.6153.1
96.025.6150.8

signal brown

96.025.2151.4

96.025.6151.4

without
ferruleswithout
ferrules

RST® CLASSIC

Application

with spring clamp connection

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

250V

Coding

Color
N, L
–, +

~50/-120V
1, 2

1)

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M16 x 1.5
insideFerruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M16 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.026.2153.0
96.026.2153.1
96.026.2150.8

96.026.6153.0
96.026.6153.1
96.026.6150.8

signal brown

96.026.2151.4

96.026.6151.4

without
ferruleswithout
ferrulesWith wire protection available on request

81

RST 20i2

M20 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

Coding250Vwith spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M20 x 1.5
inside

Color

L, N
+, –

~50/-120V
1, 2

Ferruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M20 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.021.2053.0
96.021.2053.1

96.021.6053.0
96.021.6053.1
96.021.6050.8

signal brown

96.021.2051.4

96.021.6051.4

without
ferruleswithout
ferrulesMale connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip lengths aswell as the ferrules to be used.

Application

250V~50/-120V

Coding

Color

L, N
+, –
1, 2

1)

82

With wire protection available on request

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M20 x 1.5
insideFerruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M20 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.022.2053.0
96.022.2053.1

96.022.6053.0
96.022.6053.1
96.022.6050.8

signal brown

96.022.2051.4

96.022.6051.4

without
ferruleswithout
ferrulesRST 20i2

M20 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Coding250Vwith screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M20 x 1.5
inside

Color
L, N
+, –

~50/-120V
1, 2

Ferruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M20 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.023.2053.0
96.023.2053.1
96.023.2050.8

96.023.6053.0
96.023.6053.1
96.023.6050.8

signal brown

96.023.2051.4

96.023.6051.4

without
ferruleswithout
ferrules

RST® CLASSIC

Application

with spring clamp connection

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

250V

Coding

Color

L, N
+, –

~50/-120V
1, 2

1)

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M20 x 1.5
insideFerruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M20 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.024.2053.0
96.024.2053.1
96.024.2050.8

96.024.6053.0
96.024.6053.1
96.024.6050.8

signal brown

96.024.2051.4

96.024.6051.4

without
ferruleswithout
ferrulesWith wire protection available on request

83

RST 20i2

M25 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

Coding250Vwith screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M25 x 1.5
inside

Color
L, N
+, –

~50/-120V

with spring clamp connection

1, 2

Ferruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M25 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.023.2253.0
96.023.2253.1
96.023.2250.8

96.023.6253.0
96.023.6253.1
96.023.6250.8

signal brown

96.023.2251.4

96.023.6251.4

without
ferruleswithout
ferrulesMale connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
90° angle.
See the Technical Data for insulation strip lengths aswell as the ferrules to be used.

Application

250V

Coding

Color
L, N
+, –

~50/-120V
1, 2

1)

84

With wire protection available on request

with spring clamp connection

with screw connection1)

Wire
rigid

mm2
0.5 – 2.5

Wire
rigid

fine-stranded

0.5 – 1.5

stranded

0.75 – 1.5

Term. poles
ThreadGland2
M25 x 1.5
insideFerruleswithferruleswithferrulesfine-stranded

mm20.75 – 6.0

strandedTerm. poles
ThreadGland1
M25 x 1.5
insidePart No.

Part No.

light grayblack
pebble gray96.024.2253.0
96.024.2253.1
96.024.2250.8

96.024.6253.0
96.024.6253.1
96.024.6250.8

signal brown

96.024.2251.4

96.024.6251.4

without
ferruleswithout
ferrulesRST® CLASSIC

RST 20i2

85RST 20i2

Cable assemblies

Cable 2 x 1.5 mm2; 16 A
Rated values

Pull relief

shrinkage tube

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

black

Wire strip length(open cable end)

9 mm

Color shrinkage tube

black

Connection cables female – male

250V
black

~50/-120V
signal brown
N = BUL = BNCable
PVC cable
H05VV-F
containing halogen

Cable
Rubber-sheathed cable
H07RN-F
containing halogen

12~50/-120V
pebble gray
= BU
= BN

– = BU+ = BN

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1000.1
96.222.2000.1
96.222.3000.1
96.222.4000.1
96.222.5000.1
96.222.6000.1
96.222.7000.1
96.222.8000.1

96.222.1002.4
96.222.2002.4
96.222.3002.4
96.222.4002.4
96.222.5002.4
96.222.6002.4
96.222.7002.4
96.222.8002.4

on request

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1030.1
96.222.2030.1
96.222.3030.1
96.222.4030.1
96.222.5030.1
96.222.6030.1
96.222.7030.1
96.222.8030.1

96.222.1032.4
96.222.2032.4
96.222.3032.4
96.222.4032.4
96.222.5032.4
96.222.6032.4
96.222.7032.4
96.222.8032.4

on request

250V
black

~50/-120V
signal brown~50/-120V
pebble gray2-pole connectors – one pole is notconfigured.

Connection cables female – free end

N = BUL = BNCable
PVC cable
H05VV-F
containing halogen

Cable
Rubber-sheathed cable
H07RN-F
containing halogen

2-pole connectors – one pole is notconfigured.

86

Other cable lengths, other codings upon request

1
2

= BU
= BN

– = BU+ = BN

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1003.1
96.222.2003.1
96.222.3003.1
96.222.4003.1
96.222.5003.1
96.222.6003.1
96.222.7003.1
96.222.8003.1

96.222.1007.4
96.222.2007.4
96.222.3007.4
96.222.4007.4
96.222.5007.4
96.222.6007.4
96.222.7007.4
96.222.8007.4

on request

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1033.1
96.222.2033.1
96.222.3033.1
96.222.4033.1
96.222.5033.1
96.222.6033.1
96.222.7033.1
96.222.8033.1

96.222.1037.4
96.222.2037.4
96.222.3037.4
96.222.4037.4
96.222.5037.4
96.222.6037.4
96.222.7037.4
96.222.8037.4

on request

RST 20i2

Cable assemblies

Cable 2 x 1.5 mm2; 16 A

Connection cables male – free end

250V
black

~50/-120V
signal brown

N = BUL = BNPVC cable
H05VV-F
containing halogen

Cable
Rubber-sheathed cable
H07RN-F
containing halogen

= BU
= BN

– = BU+ = BN

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1004.1
96.222.2004.1
96.222.3004.1
96.222.4004.1
96.222.5004.1
96.222.6004.1
96.222.7004.1
96.222.8004.1

96.222.1008.4
96.222.2008.4
96.222.3008.4
96.222.4008.4
96.222.5008.4
96.222.6008.4
96.222.7008.4
96.222.8008.4

on request

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1034.1
96.222.2034.1
96.222.3034.1
96.222.4034.1
96.222.5034.1
96.222.6034.1
96.222.7034.1
96.222.8034.1

96.222.1038.4
96.222.2038.4
96.222.3038.4
96.222.4038.4
96.222.5038.4
96.222.6038.4
96.222.7038.4
96.222.8038.4

on request

RST® CLASSIC

Cable

1
2

~50/-120V
pebble gray2-pole connectors – one pole is notconfigured.

Power Connection cable
Male: CEE 7/17 unearthed plug – female: RST®

250V
black
Cable
Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No..

1.5

99.708.0000.7

87

RST 20i2

Cable assemblies

Cable 2 x 1.5 mm2; 16 A
Rated values
Wire ends

Pull relief(open cable end)

shrinkage tube

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cablegray

Wire strip length

9 mm

Color shrinkage tube

black

(open cable end)

Connection cables female – male~50/-120V
pebble gray~50/-120V
signal brown– = BU+ = BNCable

PVC cableÖlflex Classic 100
containing halogen

1
2

= BU
= BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1092.8
96.222.2092.8
96.222.3092.8
96.222.4092.8
96.222.5092.8
96.222.6092.8
96.222.7092.8
96.222.8092.8

96.222.1092.4
96.222.2092.4
96.222.3092.4
96.222.4092.4
96.222.5092.4
96.222.6092.4
96.222.7092.4
96.222.8092.4~50/-120V
pebble gray~50/-120V
signal brown

2-pole connectors – one pole is notconfigured.

Connection cables female – free end– = BU+ = BNCable

PVC cableÖlflex Classic 100
containing halogen

2-pole connectors – one pole is not configured.

88

Other cable lengths, other codings upon request

1
2

= BU
= BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1097.8
96.222.2097.8
96.222.3097.8
96.222.4097.8
96.222.5097.8
96.222.6097.8
96.222.7097.8
96.222.8097.8

96.222.1097.4
96.222.2097.4
96.222.3097.4
96.222.4097.4
96.222.5097.4
96.222.6097.4
96.222.7097.4
96.222.8097.4

RST 20i2

Cable assemblies

Cable 2 x 1.5 mm2; 16 A

Connection cables male – free end– = BU+ = BNCable
PVC cableÖlflex Classic 100
containing halogen~50/-120V
signal brown
1
2

= BU
= BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.222.1098.8
96.222.2098.8
96.222.3098.8
96.222.4098.8
96.222.5098.8
96.222.6098.8
96.222.7098.8
96.222.8098.8

96.222.1098.4
96.222.2098.4
96.222.3098.4
96.222.4098.4
96.222.5098.4
96.222.6098.4
96.222.7098.4
96.222.8098.4

RST® CLASSIC~50/-120V
pebble gray2-pole connectors – one pole is notconfigured.

89

RST 20i2

Cable assemblies

Cable 2 x 2.5 mm2; 20 A
Rated values
Wire ends

Pull relief(open cable end)

shrinkage tube

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cablegray

Wire strip length

9 mm

Color shrinkage tube

black

(open cable end)

Connection cables female – male~50/-120V
pebble gray~50/-120V
signal brown– = BU+ = BNCable
PVC cableÖlflex Classic 100
containing halogen

1
2

= BU
= BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.223.1092.8
96.223.2092.8
96.223.3092.8
96.223.4092.8
96.223.5092.8
96.223.6092.8
96.223.7092.8
96.223.8092.8

96.223.1092.4
96.223.2092.4
96.223.3092.4
96.223.4092.4
96.223.5092.4
96.223.6092.4
96.223.7092.4
96.223.8092.4~50/-120V
pebble gray~50/-120V
signal brown

2-pole connectors – one pole is notconfigured.

Connection cables female – free end– = BU+ = BNCable
PVC cableÖlflex Classic 100
containing halogen

2-pole connectors – one pole is not configured.

90

Other cable lengths, other codings upon request

1
2

= BU
= BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.223.1097.8
96.223.2097.8
96.223.3097.8
96.223.4097.8
96.223.5097.8
96.223.6097.8
96.223.7097.8
96.223.8097.8

96.223.1097.4
96.223.2097.4
96.223.3097.4
96.223.4097.4
96.223.5097.4
96.223.6097.4
96.223.7097.4
96.223.8097.4

RST 20i2

Cable assemblies

Cable 2 x 2.5 mm2; 20 A

Connection cables male – free end– = BU+ = BNCable
PVC cableÖlflex Classic 100
containing halogen~50/-120V
signal brown
1
2

= BU
= BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.223.1098.8
96.223.2098.8
96.223.3098.8
96.223.4098.8
96.223.5098.8
96.223.6098.8
96.223.7098.8
96.223.8098.8

96.223.1098.4
96.223.2098.4
96.223.3098.4
96.223.4098.4
96.223.5098.4
96.223.6098.4
96.223.7098.4
96.223.8098.4

RST® CLASSIC~50/-120V
pebble gray2-pole connectors – one pole is notconfigured.

91

RST 20i2

Distribution block
Distribution block 1I/3O (parallel connection),for protection class II, AS-i or LEDs

InterlockYeswith fastening option
Colorn blackn light greyn pebble grayn signal brown

Application
250V
250V
~50/-120V~50/-120V

Pole marking
L, N
L, N
+, –
1, 2

Input
1
1
1
1

Outputs
3
3
3
3

Part No.
96.020.0153.1
96.020.0153.0
96.020.0150.8
96.020.0151.4

Pole marking
L, N
L, N
+, –
1, 2

Input
1
1
1
1

Outputs
3
3
3
3

Part No.
96.020.0253.1
96.020.0253.0
96.020.0250.8
96.020.0251.4

Application~50/-120V

Pole marking
1, 2

Input
1

Outputs
3

Part No.
99.910.0000.7

Application~50/-120V

Pole marking
1, 2

without fastening option
Circuit diagram

Colorn blackn light greyn pebble grayn signal brown

Application
250V
250V
~50/-120V~50/-120V

Distribution block 1 I/3 O(series connection) for power LEDs
with fastening option
Colorn signal brown

Circuit diagram

jumper plugColorn signal brown

For jumpering od unused slots on the series
distribution unit
e.g. circuit diagrams

92

Part No.
99.537.0000.7

RST 20i2

Distribution unit
RST compact distribution unit 1I/2O

Fitted as required with

M25 device connectors 2-pole

Dimensions

Pre-wired with

2.5 mm2 (halogen free)

Mounting option

Yes

104 x 162 x 57.2 mm

Color
n black

Input
1, RST20i2

Outputs
2, RST20i2

Part No.
99.942.0000.7

Outputs
3, RST20i2
3, RST20i2

Part No.
99.990.0000.7
upon request

Outputs
7, RST20i2
7, RST20i2

Part No.
99.946.0000.7
99.988.0000.7

Circuit diagram2

2
2Compact distribution unit 1I/3O

Fitted as required with

M25 device connectors 2-pole

Dimensions

Pre-wired with

2.5 mm2 (halogen free)

Mounting option

Yes

104 x 162 x 57.2 mm

Color
n light grayn black

Input
1, RST20i2
1, RST20i2

2

2

2

2

Multi distribution unit 1I/7O

Fitted as required with

M25 device connectors 2-pole

Dimensions

Pre-wired with

2,5 mm2 (halogen free)Fuses

6.3 or 10A can be integrated

104 x 162 x 96 mm

Colorn signal brownn black

Input
1, RST20i2
1, RST20i2

RST® CLASSIC

Circuit diagram

Circuit diagram

2

2

2

2

2

2

2

2

Detailed information about the distribution units available in section ”Compact/Multiple distribution units“.

93RST 20i2

Connector for pole socket, straight

For cables Ø 6 - 10 mm and Illumination cable 13.3 x 5.3

Male connector
Unmounted with screwed cable gland.
Without locking slide Safety Clip.
Sheath stripping and insulation removal
lengths refer to Technical data.

with screw connection1)
Wire
rigid
fine-stranded
stranded

Application

Coding

250V

L, N

mm2
0.75 – 6.02)

Ø cable mm

Color

Part No.

6 – 10black

99.592.0000.7

for illumination cable 13.3 x 5.3
H05RNH2-F2 x 1.5²

black

99.593.0000.7

Cable assembly for pole socket
Cable 2 x 1.5 mm2; 16 A
Rated values

Pull relief

shrinkage tube

Wire ends

ultrason. weldedInterlockIntegrated

Sheath strip length

30 mm

Color cable

black

Wire strip length

9 mm

Color shrinkage tube

black

Connection cables female - free end

250V
black
N = BUL = BN

Cable

Length m

Part No.

1
2
3
4
5
6
9

99.504.0000.7
99.505.0000.7
99.506.0000.7
99.507.0000.7
99.508.0000.7
99.511.0000.7
99.534.0000.7

PVC cable
H05VV-F
containing halogen

2-pole connectors – one pole is notconfigured.

94

1)
2)

With wire protection available on request
With 6.0 mm2 wires the pull and bending forces at the connector must be taken into consideration and compensated by suitable measures if required

RST® CLASSIC

RST 20i2

95

RST 20i3

96

RST 20i3

Standard variant for network applications – polyphasesystems, switching applications 250 V and low voltage
Application example

GeneralWith the 3-pole connectors, there
are four available variants: Threeversions for applications up to
250/400V (e.g. general network
applications, switching applications,applications for multiphase systems)
and a version for extra-low voltages
up to ~50/-120V. All connectors aremechanically coded. This means that
only associated pairs of male andfemale can be connected with thecorrect polarity. You therefore havethe security of a clear separation ofdifferent applications without having
to redo any incorrect connections.

RST ® CLASSIC

The color of the connectors indicatesthe links that belong together.

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

Name

Description
1 x cable entry

Connector
2 x cable entry

Connection
style
Screw
Spring clamp
Crimp
Screw
Spring clamp
Crimp

Strain relief
housing

Connection points
per pole

yes

1

yes

2

RST compact distribution unit /multi-distribution unit

Deviceconnectors

Cable
assemblies

1, 2, light graypreassembled
preassembled
preassembled
preassembled

1, 2, 3

1, 2, preassembled
preassembled
preassembled
preassembled

preassembled
preassembled
preassembled
preassembled

black

leaf green light blue

signalbrownü ü ü ü üü ü üü ü ü ü üonrequestonrequestIndividual distribution box
M16 device connector,
modular, straightM16 device connector,
modular, angled 7°
M25 device connector,
standard
M20 device connector,
standard
M20 device connector,
modular, straightM25 device connector,
modular, angled
Connection cableMale – Free end
Connection cable
Female – Free end
Extension cableMale – Female
Connection cable
Schuko – Female

250/400V 250/400V ~50/-120V

MechanicalcodingDistribution block 1I/3O
Distribution units

250V
L, N, onrequestonrequestonrequestonrequestonrequestonrequestü ü ü üü ü ü üü ü ü üü ü ü üü ü ü üü ü ü ü
ü ü ü
ü ü ü
ü ü ü
ü ü

on
requestonrequest

ü
ü
ü
ü
ü
ü
ü
ü
ü

97

RST 20i3

Connectors, straightfor cables Ø 6 – 10 mm and 10 – 14 mm

Female connector
Unmounted with cable gland.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingCable diameter in mm

6 – 10L, N,

250/400V

10 – 141, 2,
3~50/-120V

1, 2,

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
stranded

Wire
rigid
fine-stranded
strandedWire
fine-stranded

Color

light grayblack
light grayblack

6 – 10leaf green
10 –14
6 – 10light blue
10 –14
6 – 10signalbrown
10 –141, 2,
with spring clamp conn.
mm
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2

mm

2

0.75 – 6.02)

mm20.75 – 4.0

Part No.

Part No.

Part No.

96.031.0053.0
96.031.0053.1
96.031.0153.0
96.031.0153.1
96.031.0055.7
96.031.0155.7
96.031.0053.9
96.031.0153.9
96.031.0051.4
96.031.0151.4

96.031.4053.0
96.031.4053.1
96.031.4153.0
96.031.4153.1
96.031.4055.7
96.031.4155.7
96.031.4053.9
96.031.4153.9
96.031.4051.4
96.031.4151.4

96.131.0053.0
96.131.0053.1
96.131.0153.0
96.131.0153.1

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp conn.

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
stranded

Wire
rigid
fine-stranded
strandedWire
fine-stranded

Male connector
Unmounted with cable gland and locking
device.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingN, L,250/400V

2, 1,

2, 1
3

~50/-120V

2, 1,

Cable diameter in mm

6 – 10
10 – 14Colorlight grayblack
light grayblack

6 – 10leaf green
10 –14
6 – 10light blue
10 –14
6 – 10signalbrown
10 –14mm
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2

1)
2)

0.75 – 6.02)

mm20.75 – 4.0

Part No.

Part No.

Part No.

96.032.0053.0
96.032.0053.1
96.032.0153.0
96.032.0153.1
96.032.0055.7
96.032.0155.7
96.032.0053.9
96.032.0153.9
96.032.0051.4
96.032.0151.4

96.032.4053.0
96.032.4053.1
96.032.4153.0
96.032.4153.1
96.032.4055.7
96.032.4155.7
96.032.4053.9
96.032.4153.9
96.032.4051.4
96.032.4151.4

96.132.0053.0
96.132.0053.1
96.132.0153.0
96.132.0153.1

Fine-stranded and stranded wires only withferrules (see accessories)

98

mm

2

Fine-stranded and stranded wires without
ferrulesWith wire protection available on request
With 6.0 mm2 wires the pull and bending forces at the connector must be taken into consideration and compensated by suitable measures if required

Contacts separately under Accessories.

RST 20i3

Connectors, angled 90°

for cables Ø 6 – 10 mm and 10 – 14 mm

Female connector
Unmounted with cable gland.
90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

CodingCable diameter in mm

6 – 10L, N,

250/400V

10 – 141, 2,
3~50/-120V

1, 2,

with crimp connection

Wire
rigid
fine-stranded
stranded

Wire
rigid
fine-stranded
strandedWire
fine-stranded

Color

light grayblack
light grayblack

6 – 10leaf green
10 –14
6 – 10light blue
10 –14
6 – 10signalbrown
10 –141, 2,
with screw connection1)mm
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2

mm

2

0.75 – 6.02)

mm20.75 – 4.0

Part No.

Part No.

Part No.

96.033.0053.0
96.033.0053.1
96.033.0153.0
96.033.0153.1
96.033.0055.7
96.033.0155.7
96.033.0053.9
96.033.0153.9
96.033.0051.4
96.033.0151.4

96.033.4053.0
96.033.4053.1
96.033.4153.0
96.033.4153.1
96.033.4055.7
96.033.4155.7
96.033.4053.9
96.033.4153.9
96.033.4051.4
96.033.4151.4

96.133.0053.0
96.133.0053.1
96.133.0153.0
96.133.0153.1

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp conn.

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
stranded

Wire
rigid
fine-stranded
strandedWire
fine-stranded

RST ® CLASSIC

Application

with spring clamp conn.

Male connector
Unmounted with cable gland and locking
device. 90° angle.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

CodingN, L,250/400V

2, 1,

2, 1
3

~50/-120V

2, 1,

Cable diameter in mm

6 – 10
10 – 14Colorlight grayblack
light grayblack

6 – 10leaf green
10 –14
6 – 10light blue
10 –14
6 – 10signalbrown
10 –14mm
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2

2)

0.75 – 6.02)

mm20.75 – 4.0

Part No.

Part No.

Part No.

96.034.0053.0
96.034.0053.1
96.034.0153.0
96.034.0153.1
96.034.0055.7
96.034.0155.7
96.034.0053.9
96.034.0153.9
96.034.0051.4
96.034.0151.4

96.034.4053.0
96.034.4053.1
96.034.4153.0
96.034.4153.1
96.034.4055.7
96.034.4155.7
96.034.4053.9
96.034.4153.9
96.034.4051.4
96.034.4151.4

96.134.0053.0
96.134.0053.1
96.134.0153.0
96.134.0153.1

Fine-stranded and stranded wires only withferrules (see accessories)

1)

mm

2

Fine-stranded and stranded wires without
ferrulesWith wire protection available on request
With 6.0 mm2 wires the pull and bending forces at the connector must be taken into consideration and compensated by suitable measures if required

Contacts separately under Accessories.

99

RST 20i3

Connectors, straightfor cables Ø 13 – 18 mm

Female connector
Unmounted with cable gland.
See Technical Data for sheath and insulation strip
lengths.

Application

Coding250/400V

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-strandedmm

20.75 – 6.02)

without ferrules
without ferrules

mm20.75 – 4.0

Cable diameter in mm

Color

Part No.

Part No.

L, N,


13 –18light grayblack

96.031.4553.0
96.031.4553.1

96.131.4553.0
96.131.4553.1

1, 2,


13 –18 leaf green

96.031.4555.7

2, 1
3

13 –1896.031.4553.9

light blue

Fine-stranded and stranded wires without ferrules

Contacts separately under Accessories.

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

Male connector
Unmounted with cable gland and locking device.
See Technical Data for sheath and insulation strip
lengths.

Application

250/400V

CodingCable diameter in mm

Color

N, L,


13 –18mm

20.75 – 6.02)

without ferrules
without ferrules

Part No.

Part No.

light grayblack

96.032.4553.0
96.032.4553.1

96.132.4553.0
96.132.4553.1

2, 1,


13 –18 leaf green

96.032.4555.7

2, 1
3

13 –1896.032.4553.9

light blue

Fine-stranded and stranded wires without ferrules

1)

With wire protection available on request

100 With 6.0 mm wires the pull and bending forces at the connector must be taken into consideration and compensated by suitable measures if required
2)

2

mm2
0.75 – 4.0

Contacts separately under Accessories.

RST 20i3

Splitter connector, straightfor cables Ø 6 – 10 mm and 10 – 14 mm

Female connector
Unmounted with cable gland.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

CodingCable diameter in mm

L, N,


250/400V

1, 2,

1, 2,
3

6 – 10
10 – 14with screw connection1)

Leitungenrigidfine-stranded
stranded

Leitungenrigidfine-stranded
stranded

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5

Colorlight grayblack
light grayblack

6 – 10leaf green
10 – 1410 – 14light blue

with ferruleswith ferrules

mm20.75 – 2.5

Part No.

Part No.

96.031.0253.0
96.031.0253.1
96.031.0353.0
96.031.0353.1
96.031.0255.7
96.031.0355.7

96.031.4253.0
96.031.4253.1
96.031.4353.0
96.031.4353.1
96.031.4255.7
96.031.4355.7

96.031.0353.9

Fine-stranded and stranded wires only with ferrules (see accessories)

RST ® CLASSIC

Application

with spring clamp connection

Fine-stranded and stranded wires without ferrules

Mounting plate for splitter connectors
Colorn grayn black

1)

With wire protection available on request

Part No.
01.006.1553.0
01.006.1553.1

101

RST 20i3

M25 device connector
straight, standard

Female connector
Correct positioning guaranteed due toflattened thread. Fastening with screws
from outside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.
For the spacer rings for unlocking thedevice connectors, see Accessories.

Application

Coding250/400V~50/-120V

with spring clamp conn.

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

Color

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M25 x 1.5
outsidemm20.75 – 6.0
1
M25 x 1.5
outsidemm20.75 – 4.0
1
M25 x 1.5
outsidePart No.

Part No.

Part No.

L, N, light grayblack

96.031.1053.0
96.031.1053.1

96.031.5053.0
96.031.5053.1

96.131.1053.0
96.131.1053.1

1, 2, leaf green

96.031.1055.7

96.031.5055.7

96.131.1055.7

1, 2, 3light blue

96.031.1053.9

96.031.5053.9

1, 2, signal brown

96.031.1051.4

96.031.5051.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp conn.

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandMale connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from outside.
With locking device.
See the Technical Data for insulation strip
lengths.

Application

250/400V~50/-120V

CodingColor

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M25 x 1.5
outside0.75 – 6.0
1
M25 x 1.5
outsidemm20.75 – 4.0
1
M25 x 1.5
outsidePart No.

Part No.

Part No.

N, L, light grayblack

96.032.1053.0
96.032.1053.1

96.032.5053.0
96.032.5053.1

96.132.1053.0
96.132.1053.1

2, 1, leaf green

96.032.1055.7

96.032.5055.7

96.132.1055.7

2, 1, 3light blue

96.032.1053.9

96.032.5053.9

2, 1, signal brown

96.032.1051.4
Fine-stranded and stranded wires only withferrules (see accessories)

102

mm2

96.032.5051.4
Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

RST 20i3

M20 device connector
straight, modular

Female connector
Correct positioning guaranteed due toflattened thread. Fastening with screws
from inside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Coding250/400V~50/-120V

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

Color

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M20 x 1.5
insidemm20.75 – 6.0
1
M20 x 1.5
insidemm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

Part No.

L, N, light grayblack

96.031.2053.0
96.031.2053.1

96.031.6053.0
96.031.6053.1

96.131.2053.0
96.131.2053.1

1, 2, leaf green

96.031.2055.7

96.031.6055.7

1, 2, 3light blue

96.031.2053.9

96.031.6053.9

1, 2, signal brown

96.031.2051.4

96.031.6051.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGland

RST ® CLASSIC

Application

with spring clamp connection

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip
lengths.

Application

250/400V~50/-120V

CodingColor

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M20 x 1.5
insidemm20.75 – 6.0
1
M20 x 1.5
insidemm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

Part No.

96.132.2053.0
96.132.2053.1

N, L, light grayblack

96.032.2053.0
96.032.2053.1

96.032.6053.0
96.032.6053.1

2, 1, leaf green

96.032.2055.7

96.032.6055.7

2, 1, 3light blue

96.032.2053.9

96.032.6053.9

2, 1, signal brown

96.032.2051.4

96.032.6051.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

103

RST 20i3

M16 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

Coding250/400V~50/-120V

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

Color

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M16 x 1.5
insidemm20.75 – 6.0
1
M16 x 1.5
insidemm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

Part No.

L, N, light grayblack

96.031.2153.0
96.031.2153.1

96.031.6153.0
96.031.6153.1

96.131.2153.0
96.131.2153.1

1, 2, leaf green

96.031.2155.7

96.031.6155.7

1, 2, 3light blue

96.031.2153.9

96.031.6153.9

1, 2, signal brown

96.031.2151.4

96.031.6151.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandMale connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip
lengths.

Application

250/400V~50/-120V

CodingColor

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M16 x 1.5
inside0.75 – 6.0
1
M16 x 1.5
insidemm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

Part No.

96.132.2153.0
96.132.2153.1

N, L, light grayblack

96.032.2153.0
96.032.2153.1

96.032.6153.0
96.032.6153.1

2, 1, leaf green

96.032.2155.7

96.032.6155.7

2, 1, 3light blue

96.032.2153.9

96.032.6153.9

2, 1, signal brown

96.032.2151.4
Fine-stranded and stranded wires only withferrules (see accessories)

104

mm2

96.032.6151.4
Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

RST 20i3

M16 device connector
angled 7°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 7°, thread M16.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Coding250/400V~50/-120V

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

Color

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M16 x 1.5
insidemm20.75 – 6.0
1
M16 x 1.5
insidemm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

Part No.

L, N, light grayblack

96.035.2153.0
96.035.2153.1

96.035.6153.0
96.035.6153.1

96.135.2153.0
96.135.2153.1

1, 2, leaf green

96.035.2155.7

96.035.6155.7

1, 2, 3light blue

96.035.2153.9

96.035.6153.9

1, 2, signal brown

96.035.2151.4

96.035.6151.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGland

RST ® CLASSIC

Application

with spring clamp connection

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
Angled 7°, thread M16.
See the Technical Data for insulation strip
lengths.

Application

250/400V~50/-120V

CodingColor

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M16 x 1.5
insidemm20.75 – 6.0
1
M16 x 1.5
insidemm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

Part No.

96.136.2153.0
96.136.2153.1

N, L, light grayblack

96.036.2153.0
96.036.2153.1

96.036.6153.0
96.036.6153.1

2, 1, leaf green

96.036.2155.7

96.036.6155.7

2, 1, 3light blue

96.036.2153.9

96.036.6153.9

2, 1, signal brown

96.036.2151.4
Fine-stranded and stranded wires only withferrules (see accessories)

96.036.6151.4
Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

105

RST 20i3

M20 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
See the Technical Data for insulation strip
lengths as well as the ferrules to be used.

Application

Coding250/400V~50/-120V

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

Color

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M20 x 1.5
insidemm20.75 – 6.0
1
M20 x 1.5
insidemm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

Part No.

L, N, light grayblack

96.033.2053.0
96.033.2053.1

96.033.6053.0
96.033.6053.1

96.133.2053.0
96.133.2053.1

1, 2, leaf green

96.033.2055.7

96.033.6055.7

1, 2, 3light blue

96.033.2053.9

96.033.6053.9

1, 2, signal brown

96.033.2051.4

96.033.6051.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandMale connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip
lengths.

Application

250/400V~50/-120V

CodingColor

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M20 x 1.5
inside0.75 – 6.0
1
M20 x 1.5
insidemm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

Part No.

96.134.2053.0
96.134.2053.1

N, L, light grayblack

96.034.2053.0
96.034.2053.1

96.034.6053.0
96.034.6053.1

2, 1, leaf green

96.034.2055.7

96.034.6055.7

2, 1, 3light blue

96.034.2053.9

96.034.6053.9

2, 1, signal brown

96.034.2051.4
Fine-stranded and stranded wires only withferrules (see accessories)

106

mm2

96.034.6051.4
Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

RST 20i3

M25 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
See the Technical Data for insulation strip lengths
as well as the ferrules to be used.

Coding250/400V~50/-120V

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

Color

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M25 x 1.5
insidemm20.75 – 6.0
1
M25 x 1.5
insidemm20.75 – 4.0
1
M25 x 1.5
insidePart No.

Part No.

Part No.

L, N, light grayblack

96.033.2253.0
96.033.2253.1

96.033.6253.0
96.033.6253.1

96.133.2253.0
96.133.2253.1

1, 2, leaf green

96.033.2255.7

96.033.6255.7

1, 2, 3light blue

96.033.2253.9

96.033.6253.9

1, 2, signal brown

96.033.2251.4

96.033.6251.4

Fine-stranded and stranded wires only withferrules (see accessories)

Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

with spring clamp connection

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
Thread
Gland

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGland

RST ® CLASSIC

Application

with spring clamp connection

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
See the Technical Data for insulation strip
lengths.

Application

250/400V~50/-120V

CodingColor

mm2
0.5 – 2.5
0.5 – 1.5
0.75 – 1.5
2
M25 x 1.5
insidemm20.75 – 6.0
1
M25 x 1.5
insidemm20.75 – 4.0
1
M25 x 1.5
insidePart No.

Part No.

Part No.

96.134.2253.0
96.134.2253.1

N, L, light grayblack

96.034.2253.0
96.034.2253.1

96.034.6253.0
96.034.6253.1

2, 1, leaf green

96.034.2255.7

96.034.6255.7

2, 1, 3light blue

96.034.2253.9

96.034.6253.9

2, 1, signal brown

96.034.2251.4
Fine-stranded and stranded wires only withferrules (see accessories)

96.034.6251.4
Fine-stranded and stranded wires without
ferrulesContacts separately under Accessories.

107

RST 20i3

Cable assemblies

Cable 3 x 1.5 mm2; 16 A
Rated values
Wire ends

Pull relief(open cable end)

shrinkage tube

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cable

black

Wire strip length

9 mm

Color shrinkage tube

black

(open cable end)

Connection cables female – male

250V
black

250/400V
leaf green
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-freePart No.

Part No.

1
2
3
4
5
6
7
8

96.232.1000.1
96.232.2000.1
96.232.3000.1
96.232.4000.1
96.232.5000.1
96.232.6000.1
96.232.7000.1
96.232.8000.1

96.232.1001.7
96.232.2001.7
96.232.3001.7
96.232.4001.7
96.232.5001.7
96.232.6001.7
96.232.7001.7
96.232.8001.7

containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

108 Other cable lengths, other codings upon request

= BN
= BU
= BK

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.232.1030.1
96.232.2030.1
96.232.3030.1
96.232.4030.1
96.232.5030.1
96.232.6030.1
96.232.7030.1
96.232.8030.1

96.232.1031.7
96.232.2031.7
96.232.3031.7
96.232.4031.7
96.232.5031.7
96.232.6031.7
96.232.7031.7
96.232.8031.7

96.232.1010.9
96.232.2010.9
96.232.3010.9
96.232.4010.9
96.232.5010.9
96.232.6010.9
96.232.7010.9
96.232.8010.9

250/400V
leaf green

250/400V
light blue

Length m

Part No.

1
2
3
4
5
6
7
8

96.232.1050.1
96.232.2050.1
96.232.3050.1
96.232.4050.1
96.232.5050.1
96.232.6050.1
96.232.7050.1
96.232.8050.1

250 V
black
 = GN/YE
N = BUL = BNPVC cable
H05VV-F

3
2
1

 = GN/YE
1 = BU
2 = BN

Length mConnection cables female – free end

Cable

250/400V
light blue

 = GN/YE
1 = BU
2 = BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.232.1003.1
96.232.2003.1
96.232.3003.1
96.232.4003.1
96.232.5003.1
96.232.6003.1
96.232.7003.1
96.232.8003.1

96.232.1005.7
96.232.2005.7
96.232.3005.7
96.232.4005.7
96.232.5005.7
96.232.6005.7
96.232.7005.7
96.232.8005.7

3
2
1

= BN
= BU
= BK

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.232.1033.1
96.232.2033.1
96.232.3033.1
96.232.4033.1
96.232.5033.1
96.232.6033.1
96.232.7033.1
96.232.8033.1

96.232.1035.7
96.232.2035.7
96.232.3035.7
96.232.4035.7
96.232.5035.7
96.232.6035.7
96.232.7035.7
96.232.8035.7

on request

Length m

Part No.

1
2
3
4
5
6
7
8

96.232.1053.1
96.232.2053.1
96.232.3053.1
96.232.4053.1
96.232.5053.1
96.232.6053.1
96.232.7053.1
96.232.8053.1

RST 20i3

Cable assemblies

Cable 3 x 1.5 mm2; 16 A

250V
black
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

250/400V
leaf green
 = GN/YE
1 = BU
2 = BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.232.1004.1
96.232.2004.1
96.232.3004.1
96.232.4004.1
96.232.5004.1
96.232.6004.1
96.232.7004.1
96.232.8004.1

96.232.1006.7
96.232.2006.7
96.232.3006.7
96.232.4006.7
96.232.5006.7
96.232.6006.7
96.232.7006.7
96.232.8006.7

250/400V
light blue
3
2
1

Length m

Part No.

Part No.

Part No.

1
2
3
4
5
6
7
8

96.232.1034.1
96.232.2034.1
96.232.3034.1
96.232.4034.1
96.232.5034.1
96.232.6034.1
96.232.7034.1
96.232.8034.1

96.232.1036.7
96.232.2036.7
96.232.3036.7
96.232.4036.7
96.232.5036.7
96.232.6036.7
96.232.7036.7
96.232.8036.7

on request

Length m

Part No.

1
2
3
4
5
6
7
8

96.232.1054.1
96.232.2054.1
96.232.3054.1
96.232.4054.1
96.232.5054.1
96.232.6054.1
96.232.7054.1
96.232.8054.1

= BN
= BU
= BK

RST ® CLASSIC

Connection cables male – free end

109

RST 20i3

Cable assemblies

Cable 3 x 2.5 mm2; 20 A
Rated values

Pull relief

shrinkage tube

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

black

Wire strip length(open cable end)

9 mm

Color shrinkage tube

black

Connection cables female – male

250/400V
leaf green

250V
black
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.233.1000.1
96.233.2000.1
96.233.3000.1
96.233.4000.1
96.233.5000.1
96.233.6000.1
96.233.7000.1
96.233.8000.1

96.233.1001.7
96.233.2001.7
96.233.3001.7
96.233.4001.7
96.233.5001.7
96.233.6001.7
96.233.7001.7
96.233.8001.7

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.233.1030.1
96.233.2030.1
96.233.3030.1
96.233.4030.1
96.233.5030.1
96.233.6030.1
96.233.7030.1
96.233.8030.1

96.233.1031.7
96.233.2031.7
96.233.3031.7
96.233.4031.7
96.233.5031.7
96.233.6031.7
96.233.7031.7
96.233.8031.7

Length m

Part No.

1
2
3
4
5
6
7
8

96.233.1050.1
96.233.2050.1
96.233.3050.1
96.233.4050.1
96.233.5050.1
96.233.6050.1
96.233.7050.1
96.233.8050.1

Connection cables female – free end

250V
black
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free110 = GN/YE
1 = BU
2 = BN

250/400V
leaf green
 = GN/YE
1 = BU
2 = BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.233.1003.1
96.233.2003.1
96.233.3003.1
96.233.4003.1
96.233.5003.1
96.233.6003.1
96.233.7003.1
96.233.8003.1

96.233.1005.7
96.233.2005.7
96.233.3005.7
96.233.4005.7
96.233.5005.7
96.233.6005.7
96.233.7005.7
96.233.8005.7

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.233.1033.1
96.233.2033.1
96.233.3033.1
96.233.4033.1
96.233.5033.1
96.233.6033.1
96.233.7033.1
96.233.8033.1

96.233.1035.7
96.233.2035.7
96.233.3035.7
96.233.4035.7
96.233.5035.7
96.233.6035.7
96.233.7035.7
96.233.8035.7

Length m

Part No.

1
2
3
4
5
6
7
8

96.233.1053.1
96.233.2053.1
96.233.3053.1
96.233.4053.1
96.233.5053.1
96.233.6053.1
96.233.7053.1
96.233.8053.1

RST 20i3

Cable assemblies

Cable 3 x 2.5 mm2; 20 A

250V
black
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

250/400V
leaf green
 = GN/YE
1 = BU
2 = BN

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.233.1004.1
96.233.2004.1
96.233.3004.1
96.233.4004.1
96.233.5004.1
96.233.6004.1
96.233.7004.1
96.233.8004.1

96.233.1006.7
96.233.2006.7
96.233.3006.7
96.233.4006.7
96.233.5006.7
96.233.6006.7
96.233.7006.7
96.233.8006.7

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.233.1034.1
96.233.2034.1
96.233.3034.1
96.233.4034.1
96.233.5034.1
96.233.6034.1
96.233.7034.1
96.233.8034.1

96.233.1036.7
96.233.2036.7
96.233.3036.7
96.233.4036.7
96.233.5036.7
96.233.6036.7
96.233.7036.7
96.233.8036.7

Length m

Part No.

1
2
3
4
5
6
7
8

96.233.1054.1
96.233.2054.1
96.233.3054.1
96.233.4054.1
96.233.5054.1
96.233.6054.1
96.233.7054.1
96.233.8054.1

RST ® CLASSIC

Connection cables male – free end

111

RST 20i3

Cable assemblies

Cable 3 x 1.5 mm2; 20 A
Rated values

Pull relief

shrinkage tube

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

black

Wire strip length(open cable end)

9 mm

Color shrinkage tube

blackPower Connection cable
RST 20i3 male – Schuko coupling

250V
black
Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

0.5
1
2
3
4
5

99.719.0000.7
Other lengths
on request

Power Connection cable
Male: Schuko plug – female: RST ®

250V
gray
Cable

PVC cable
H05VV-F
containing halogen

Length m

Part No.

1.5
2.5

99.714.0000.7
99.715.0000.7

250V
black
Cable

Rubber-sheathed cable
H07RN-F
containing halogen

112

Length m

Part No.

1.5
2.5
4
5
8

99.712.0000.7
99.713.0000.7
99.716.0000.7
99.718.0000.7
99.717.0000.7

RST 20i3

Distribution units
Distribution block 1I/3O

InterlockYeswith fastening option
Colorn blackn light greyn leaf greenn signal brown

Application
250V
250V
250/400V~50/-120V

Pole marking
L, N, PE
L, N, PE1, 2, PE1, 2, PE

Input
1
1
1
1

Outputs
3
3
3
3

Part No.
96.030.0153.1
96.030.0153.0
96.030.0155.7
96.030.0151.4

Pole marking
L, N, PE
L, N, PE1, 2, PE1, 2, PE

Input
1
1
1
1

Outputs
3
3
3
3

Part No.
96.030.0253.1
96.030.0253.0
96.030.0255.7
96.030.0251.4

Outputs
3, RST20i3

Part No.
99.906.0000.7

Outputs
7, RST20i3

Part No.
99.929.0000.7

without fastening option
Colorn blackn light greyn leaf greenn signal brown

Application
250V
250V
250/400V~50/-120V

Circuit diagram

;









;
;

RST compact distribution unit
1I/3O

fitted as required with

M25 device connectors 3-pole

pre-wired with

2.5 mm2 (halogen free)

Dimensions

Mounting option

Yes

104 x 162 x 57.2 mm

Color
n black

Circuit diagram

;
;









Application

Pole marking

Input
1, RST20i3;;

RST multi-distribution unit
1I/7O

fitted as required with

M25 device connectors 3-pole

pre-wired with

2.5 mm2 (halogen free)

Dimensions

Fuse

6.3 or 10A can be integrated

104 x 162 x 96 mm

Color
n black

Circuit diagram
;
;
;
;

















RST ® CLASSIC;Application

Pole marking

Input
1, RST20i3

;
;
;
;

Detailed information about the distribution units available in section ”Distribution units“.

113RST 20i3

Connector for pole socket, straight
For cables Ø 6 - 10 mmMale connector
Unmounted with screwed cable gland.
Without locking slide Safety Clip.
Sheath stripping and insulation removal
lengths refer to Technical data.

with screw connection1)
Wire
rigid
fine-stranded
stranded

Application

Coding

250V

L, N, mm2
0.75 – 6.02)

Ø cable mm

Color

Part No.

6 – 10black

99.594.0000.7

Cable assembly for pole socket
Cable 3 x 1.5 mm2; 16 A
Rated values

Pull relief

shrinkage tube

Wire ends

ultrason. weldedInterlockIntegrated

Sheath strip length

30 mm

Color cable

black

Wire strip length

9 mm

Color shrinkage tube

black

Connection cables female - free end

250V
black
 = GN/YE
N = BUL = BN

Cable

Length m

Part No.

1
2
3
4
5
6
8
9

99.513.0000.7
99.514.0000.7
99.515.0000.7
99.516.0000.7
99.517.0000.7
99.518.0000.7
99.535.0000.7
99.533.0000.7

PVC cable
H05VV-F
containing halogen

114

1)
2)

With wire protection available on request
With 6.0 mm2 wires the pull and bending forces at the connector must be taken into consideration and compensated by suitable measures if required

RST ® CLASSIC

RST 20i3

115

RST
RST25i3
20i4

116

RST 25i3
20i4

Solar applications for systems up to 32 A for
single-phase power 3-pole

Application example

General

RST ® CLASSIC

The system is specially adapted to
the requirements of solar technology.
The connectors can be loaded witha maximum of 32 A on two contacts(L, N) and are used for single-phasepower with ENS.
Special distribution boxes are used
to bundle the electrical power of up
to 6 inverters and thus complete thesystem.
These connectors have their own
mechanical coding.
This means that only associatedpairs of male and female can beconnected with the correct polarity.
This ensures a clear separation fromthe connectors of the other productseries.

Features:■ Fast mounting through easy handling■ UV-resistant■ Rated current up to 32A (with 6.0 mm2)
■ Cross-sections up to 6 mm2■ Degree of protection IP66/68 (3m; 2h) /69

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

L, N, MechanicalcodingName

Description

Connection
style

Strain relief
housing

Connection points
per pole

Connector

1 x cable entry

Screw

yes

1

Distribution box
RST RAN Solar
Distribution box
RST Solar
M25 device connector,
standard
Connection cableMale – Free end
Connection cable
Female – Free end
Extension cableMale – Femalepreassembled
preassembled
preassembled

preassembled
preassembled
preassembled

preassembled
preassembled
preassembled

Distribution unit
Deviceconnectors
Cable
assemblies

250V

concrete gray

ü
ü
ü
ü
ü
ü
ü

117

RST 25i3

Connectors, 25A, straightfor cables Ø 10 – 14 mm and 13 – 18 mm(up to 32A with 6.0 mm²)

Female connector

Application

Coding250Vwith screw connection
for cables Ø 10 –14 mmwith screw connection
for cables Ø 13 –18 mm

Wire
solid
fine-stranded

Wire
solid
fine-stranded

mm2
up to 6.02)

Color
L, N, concrete graywithout ferrules

mm2
up to 6.02)

without ferrules

Part No.

Part No.

96.031.4154.3

96.031.4554.3

Male connector

Application

250V

1)

118

CodingColor
L, N, concrete graywith screw connection
for cables Ø 10 –14 mmwith screw connection
for cables Ø 13 –18 mm

Wire
solid
fine-stranded
Locking device

Wire
solid
fine-stranded
Locking device

mm2
up to 6.0

1)

without ferrules

yes

mm2
up to 6.01)

without ferrules

yesPart No.

Part No.

96.032.4154.3

96.032.4554.3

With 6.0 mm2 wires the pull and bending forces at the connector must be taken into consideration and compensated by suitable measures if required

RST 25i3

M25 device connector, 25 A
straight (up to 32A with 6.0 mm²)

Female connector
With sealing option
For spacer rings
for unlocking
the device connector,
see Accessories.
with screw connection
Wire
mm2
solid
up to 6.0
fine-stranded
Locking device
yesApplication

Coding250V

Color
L, N, concrete graywithout ferrules

Part No.

96.031.5054.3

Male connector
With sealing option

with screw connection
Wire
mm2
solid
up to 6.0
fine-stranded
Locking device
yes

250V

CodingColor
L, N, concrete grayPart No.

RST ® CLASSIC

Application

without ferrules

96.032.5054.3

119

RST 25i3

Cable assemblies

Cable 3 x 4.0 mm2; 25 A
Rated values

Connection type of cable

Gland nut

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cable

black

Wire strip length

9 mm

Color handle shell

black

Wire ends(open cable end)
(open cable end)

Connection cables female – male

250V
concrete gray
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.834.1000.3
96.834.1500.3
96.834.2000.3
96.834.2500.3
96.834.3000.3
96.834.3500.3
96.834.4000.3

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.834.1030.3
96.834.1530.3
96.834.2030.3
96.834.2530.3
96.834.3030.3
96.834.3530.3
96.834.4030.3

Connection cables female – free end

250V
concrete gray
 = GN/YE
N = BUL = BNCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Observe installation instructions following the product pages.

120

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.834.1003.3
96.834.1503.3
96.834.2003.3
96.834.2503.3
96.834.3003.3
96.834.3503.3
96.834.4003.3

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.834.1033.3
96.834.1533.3
96.834.2033.3
96.834.2533.3
96.834.3033.3
96.834.3533.3
96.834.4033.3

Cable diameter 11.2 mm ± 0.2
According to VDE 0281/T5 and VDE 0288/T4

Cable diameter 13.4 mm ± 0.3
According to VDE 0281/T5 and VDE 0288/T4

RST 25i3

Cable assemblies

Cable 3 x 4.0 mm2; 25 A

Connection cables male – free end

250V
concrete gray
 = GN/YE
N = BUL = BNPVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.834.1004.3
96.834.1504.3
96.834.2004.3
96.834.2504.3
96.834.3004.3
96.834.3504.3
96.834.4004.3

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.834.1034.3
96.834.1534.3
96.834.2034.3
96.834.2534.3
96.834.3034.3
96.834.3534.3
96.834.4034.3

Cable diameter 11.2 mm ± 0.2
According to VDE 0281/T5 and VDE 0288/T4

RST ® CLASSIC

Cable

Cable diameter 13.4 mm ± 0.3
According to VDE 0281/T5 and VDE 0288/T4

121

RST 20i4

122

RST 20i4

2 versions for connecting electrical drives or for routing
AS-i and extra-low voltages up to ~50/-120V

Application example

GeneralThe four pole connector is based on
the 5-pole variation with one pole notconfigured.
There are two mechanical codings.
The black or light grey coding for
applications up to 250/400V (e.g.
connection of electrical drives) andthe brown coding for extra-low voltages, for example for joint routing of
the AS Interface and the 24V auxiliary
voltage.

RST® CLASSIC

They are mechanically coded. Thismeans that only associated pairs ofmale and female can be connectedwith the correct polarity. This
ensures a clear separation from theconnectors of the other productseries.

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

Name
Connector

Distribution units

Deviceconnectors

Cable
assemblies

Description
1 x cable entry
2 x cable entry~50/-120V
1, 2, 3, 4

MechanicalcodingConnection
style
Screw
Crimp

Strain relief
housing

Connection points
per pole

yes

1

Screw

yes

1

light grayIndividual distribution box

preassembled
preassembled
preassembled

preassembled
preassembled
preassembled

preassembled
preassembled
preassembled

black

signal
brown

ü ü ü
ü ü ü

on
requestonrequest

RST compact distribution unit/
multi-distribution unit
M16 device connector,
modular, straightM16 device connector,
modular, angled 7°
M25 device connector,
standard
M20 device connector,
standard
M20 device connector,
modular, straightM25 device connector,
modular, angled
Connection cableMale – Free end
Connection cable
Female – Free end
Extension cableMale – Female

250/400V
1, 2, 3, onrequestonrequestonrequestonrequest

ü ü ü
ü ü ü
ü ü ü
ü ü ü
ü ü ü
ü ü ü
ü ü ü
ü ü ü
ü ü ü

123

RST 20i4

Connectors, straightfor cables Ø 6 – 10 mm and 10 –14 mm

Female connector
Unmounted with cable gland.
Crimp contacts separately available under
Accessories.
See Technical Data for sheath and insulation strip
lengths.

Application

CodingCable diameter in mm

6 – 10250/400V

1, 2, 3, 

~50/-120V

1, 2, 3, 4

10 – 14
6 – 101 x AS-i profile cablewith screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

Color

light grayblack
light grayblack
signal brown

mm

2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Part No.

Part No.

96.041.4053.0
96.041.4053.1
96.041.4153.0
96.041.4153.1
96.041.4051.4
96.041.4951.4

96.141.0053.0
96.141.0053.1
96.141.0153.0
96.141.0153.1

Contacts separately under Accessories, see following
pages.

Male connector
Unmounted with cable gland and locking device.
Crimp contacts separately available under
Accessories.
See Technical Data for sheath and insulation strip
lengths.

Application

CodingCable diameter in mm

6 – 10250/400V~50/-120V

1, 2, 3, 

1, 2, 3, 4

10 – 14
6 – 101 x AS-i profile cable

Colorlight grayblack
light grayblack
signal brownwith screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm

2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Part No.

Part No.

96.042.4053.0
96.042.4053.1
96.042.4153.0
96.042.4153.1
96.042.4051.4
96.042.4951.4

96.142.0053.0
96.142.0053.1
96.142.0153.0
96.142.0153.1

Contacts separately under Accessories, see following
pages.

1)

With wire protection available on request

124

RST 20i4

Connectors, angled 90°

for cables Ø 6 – 10 mm and 10 –14 mm

Female connector
Unmounted with cable gland.
90° angle.
Crimp contacts separately available under
Accessories.
See Technical Data for sheath and insulation strip
lengths.

CodingCable diameter in mm

6 – 10250/400V

1, 2, 3, 

~50/-120V

1, 2, 3, 4

10 – 14
6 – 101 x AS-i profile cable
2 x AS-i profile cablewith crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

Color

light grayblack
light grayblack
signal brown

mm

2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Part No.

Part No.

96.043.4053.0
96.043.4053.1
96.043.4153.0
96.043.4153.1
96.043.4051.4
96.043.4951.4
96.043.4851.4

96.143.0053.0
96.143.0053.1
96.143.0153.0
96.143.0153.1

RST® CLASSIC

Application

with screw connection1)

Contacts separately under Accessories, see following
pages.

Male connector
Unmounted with cable gland and locking device.
90° angle.
Crimp contacts separately available under
Accessories.
See Technical Data for sheath and insulation strip
lengths.

Application

CodingCable diameter in mm

6 – 10250/400V~50/-120V

1, 2, 3, 

1, 2, 3, 4

10 – 14
6 – 101 x AS-i profile cable
2 x AS-i profile cable

Colorlight grayblack
light grayblack
signal brownwith screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm

2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Part No.

Part No.

96.044.4053.0
96.044.4053.1
96.044.4153.0
96.044.4153.1
96.044.4051.4
96.044.4951.4
96.044.4851.4

96.144.0053.0
96.144.0053.1
96.144.0153.0
96.144.0153.1

Contacts separately under Accessories, see following
pages.

1)

With wire protection available on request

125

RST 20i4

Connectors, straightfor cables Ø 13 – 18 mm

Female connector
Unmounted with cable gland.
Crimp contacts separately available under
Accessories.
See Technical Data for sheath and insulation strip
lengths.

Application

Coding250/400V

Cable diameter in mm

Color

13 – 18

light grayblack

1, 2, 3, with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm

2

mm2
0.75 – 4.0

up to 4.0
without ferrules

Part No.

Part No.

96.041.4553.0
96.041.4553.1

96.141.0553.0
96.141.0553.1

Contacts separately under Accessories, see following
pages.

Male connector
Unmounted with cable gland and locking device.
Crimp contacts separately available under
Accessories.
See Technical Data for sheath and insulation strip
lengths.

Application

250/400V

Coding1, 2, 3, 

Cable diameter in mm

Color

13 – 18

light grayblackwith screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Part No.

Part No.

96.042.4553.0
96.042.4553.1

96.142.0553.0
96.142.0553.1

Contacts separately under Accessories, see following
pages.

1)

With wire protection available on request

126

RST 20i4

Splitter connector, straightfor cables Ø 6 – 10 mm and 10 –14 mm

Female connector
Unmounted with cable glands.
See Technical Data for sheath and insulation strip
lengths.

with screw connection1)
Wire
rigid
fine-stranded
stranded

Application

Cable diameter in mm

6 – 101, 2, 3, 

10 – 14Colorlight grayblack
light grayblack

0.75 – 1.5
without ferrules

Part No.

96.041.4253.0
96.041.4253.1
96.041.4353.0
96.041.4353.1

RST® CLASSIC

250/400V

Codingmm2

Mounting plate for splitter connectors
Colorn grayn black

1)

Part No.
01.006.1553.0
01.006.1553.1

With wire protection available on request

127

RST 20i4

M25 device connector
straight, standard

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from outside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.
For spacer rings for unlocking the device connector,
see Accessories.

Application

Codingwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

mm

2

0.75 – 4.0
without ferrules1
M25 x 1.5
outsideColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brown

mm20.75 – 4.0
1
M25 x 1.5
outsidePart No.

Part No.

96.041.5053.0
96.041.5053.1

96.141.1053.0
96.141.1053.1

96.041.5051.4

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from outside.
With locking device.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

CodingColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brownwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M25 x 1.5
outsideyes

mm20.75 – 4.0
1
M25 x 1.5
outsideyesPart No.

Part No.

96.042.5053.0
96.042.5053.1

96.142.1053.0
96.142.1053.1

96.042.5051.4

Contacts separately under Accessories, see following pages.

128

RST 20i4

M20 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Codingwith crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

mm

2

0.75 – 4.0
without ferrules
1
M20 x 1.5
insideColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brown

mm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

96.041.6053.0
96.041.6053.1

96.141.2053.0
96.141.2053.1

96.041.6051.4

RST® CLASSIC

Application

with screw connection

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
With locking device.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

CodingColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brownwith screw connection

with crimp connection

Leitungenrigidfine-stranded
strandedTerm. poles
ThreadGland
Locking device

Leitungenfine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideyes

mm20.75 – 4.0
1
M20 x 1.5
insideyesPart No.

Part No.

96.042.6053.0
96.042.6053.1

96.142.2053.0
96.142.2053.1

96.042.6051.4

Contacts separately under Accessories, see following pages.

129

RST 20i4

M16 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

Codingwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

mm

2

0.75 – 4.0
without ferrules1
M16 x 1.5
insideColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brown

mm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

96.041.6153.0
96.041.6153.1

96.141.2153.0
96.141.2153.1

96.041.6151.4

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning
Lagefixierung
durchguaranteed
Abflachen desdue Threads
to flattened
gewährleistet. Glandthread.
Fasteningvon outside.
with screws from inside.
With locking device.
Wire strip lengthn siehe unter Technical data.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

CodingColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brownwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M16 x 1.5
insideyes

mm20.75 – 4.0
1
M16 x 1.5
insideyesPart No.

Part No.

96.042.6153.0
96.042.6153.1

96.142.2153.0
96.142.2153.1

96.042.6151.4

Contacts separately under Accessories, see following pages.

1)With wire protection available on request

130

RST 20i4

M16 device connector
angled 7°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 7°, thread M16.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Codingwith crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
Thread
Gland

mm

2

0.75 – 4.0
without ferrules1
M16 x 1.5
insideColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brown

mm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

96.045.6153.0
96.045.6153.1

96.145.2153.0
96.145.2153.1

96.045.6151.4

RST® CLASSIC

Application

with screw connection

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 7°, thread M16.
With locking device.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

CodingColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brownwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M16 x 1.5
insideyes

mm20.75 – 4.0
1
M16 x 1.5
insideyesPart No.

Part No.

96.046.6153.0
96.046.6153.1

96.146.2153.0
96.146.2153.1

96.046.6151.4

Contacts separately under Accessories, see following pages.

1)With wire protection available on request

131

RST 20i4

M20 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 90°, thread M20.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

Codingwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brown

mm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

96.043.6053.0
96.043.6053.1

96.143.2053.0
96.143.2053.1

96.043.6051.4

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 90°, thread M20.
With locking device.
Crimp contacts separately available under
AccessoriesSee the Technical Data for insulation strip lengths.

Application

CodingColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brownwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideyes

mm20.75 – 4.0
1
M20 x 1.5
insideyesPart No.

Part No.

96.044.6053.0
96.044.6053.1

96.144.2053.0
96.144.2053.1

96.044.6051.4

Contacts separately under Accessories, see following pages.

1)With wire protection available on request

132

RST 20i4

M25 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 90°, thread M25.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Codingwith crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules1
M25 x 1.5
insideColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brown

mm20.75 – 4.0
1
M25 x 1.5
insidePart No.

Part No.

96.043.6253.0
96.043.6253.1

96.143.2253.0
96.143.2253.1

96.043.6251.4

RST® CLASSIC

Application

with screw connection

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 90°, thread M25.
With locking device.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

CodingColor

250/400V

1, 2, 3, light grayblack

~50/-120V

1, 2, 3, 4

signal brownwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M25 x 1.5
insideyes

mm20.75 – 4.0
1
M25 x 1.5
insideyesPart No.

Part No.

96.044.6253.0
96.044.6253.1

96.144.2253.0
96.144.2253.1

96.044.6251.4

Contacts separately under Accessories, see following pages.

1)With wire protection available on request

133

RST 20i4

Cable assemblies

Cable 4 x 1.5 mm2; 16 A
Rated values
Wire ends

Pull relief(open cable end)

Gland nut

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cable

black

Wire strip length

9 mm

Color handle shell

black(open cable end)

Connection cables female – male

250/400V
black = GN/YE
1 = BN
2 = BK
3 = BUCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1000.1
96.442.2000.1
96.442.3000.1
96.442.4000.1
96.442.5000.1
96.442.6000.1
96.442.7000.1
96.442.8000.1

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1030.1
96.442.2030.1
96.442.3030.1
96.442.4030.1
96.442.5030.1
96.442.6030.1
96.442.7030.1
96.442.8030.1

4-pole cables - one pole is not configured

Connection cables female – free end

250/400V
black = GN/YE
1 = BN
2 = BK
3 = BUCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

4-pole cables - one pole is not configured

134 Other cable lengths, other codings upon request

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1003.1
96.442.2003.1
96.442.3003.1
96.442.4003.1
96.442.5003.1
96.442.6003.1
96.442.7003.1
96.442.8003.1

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1033.1
96.442.2033.1
96.442.3033.1
96.442.4033.1
96.442.5033.1
96.442.6033.1
96.442.7033.1
96.442.8033.1

RST 20i4

Cable assemblies

Cable 4 x 1.5 mm2; 16 A

Connection cables male – free end

250/400V
black

Cable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1004.1
96.442.2004.1
96.442.3004.1
96.442.4004.1
96.442.5004.1
96.442.6004.1
96.442.7004.1
96.442.8004.1

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1034.1
96.442.2034.1
96.442.3034.1
96.442.4034.1
96.442.5034.1
96.442.6034.1
96.442.7034.1
96.442.8034.1

RST® CLASSIC = GN/YE
1 = BN
2 = BK
3 = BU

4-pole cables - one pole is not configured

135

RST 20i4

Cable assemblies

Cable 4 x 2.5 mm2; 20 A
Rated values
Wire ends

Pull relief(open cable end)

Gland nut

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cable

black

Wire strip length

9 mm

Color handle shell

black(open cable end)

Connection cables female – male

250/400V
black = GN/YE
1 = BN
2 = BK
3 = BUCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.443.1000.1
96.443.2000.1
96.443.3000.1
96.443.4000.1
96.443.5000.1
96.443.6000.1
96.443.7000.1
96.443.8000.1

Length m

Part No.

1
2
3
4
5
6
7
8

96.443.1030.1
96.443.2030.1
96.443.3030.1
96.443.4030.1
96.443.5030.1
96.443.6030.1
96.443.7030.1
96.443.8030.1

4-pole cables - one pole is not configured

Connection cables female – free end

250/400V
black = GN/YE
1 = BN
2 = BK
3 = BUCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

4-pole cables - one pole is not configured

136 Other cable lengths, other codings upon request

Length m

Part No.

1
2
3
4
5
6
7
8

96.443.1003.1
96.443.2003.1
96.443.3003.1
96.443.4003.1
96.443.5003.1
96.443.6003.1
96.443.7003.1
96.443.8003.1

Length m

Part No.

1
2
3
4
5
6
7
8

96.443.1033.1
96.443.2033.1
96.443.3033.1
96.443.4033.1
96.443.5033.1
96.443.6033.1
96.443.7033.1
96.443.8033.1

RST 20i4

Cable assemblies

Cable 4 x 2.5 mm2; 20 A

Connection cables male – free end

250/400V
black

Cable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.443.1004.1
96.443.2004.1
96.443.3004.1
96.443.4004.1
96.443.5004.1
96.443.6004.1
96.443.7004.1
96.443.8004.1

Length m

Part No.

1
2
3
4
5
6
7
8

96.443.1034.1
96.443.2034.1
96.443.3034.1
96.443.4034.1
96.443.5034.1
96.443.6034.1
96.443.7034.1
96.443.8034.1

RST® CLASSIC = GN/YE
1 = BN
2 = BK
3 = BU

4-pole cables - one pole is not configured

137

RST 20i4

Cable assemblies

Cable 4 x 1.5 mm2; 16 A
Rated values

Pull relief

Gland nut

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

grey

Wire strip length(open cable end)

9 mm

Color handle shell

black

Connection cables female – male

250/400V
black = GN/YE
1 = BK 1
2 = BK 2
3 = BK 3

Cable

PVC cableÖlflex Classic 100
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1080.1
96.442.2080.1
96.442.3080.1
96.442.4080.1
96.442.5080.1
96.442.6080.1
96.442.7080.1
96.442.8080.1

4-pole cables - one pole is not configured

Connection cables female – free end

250/400V
black = GN/YE
1 = BK 1
2 = BK 2
3 = BK 3

Cable

PVC cableÖlflex Classic 100
containing halogen

4-pole cables - one pole is not configured

138 Other cable lengths, other codings upon request

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1083.1
96.442.2083.1
96.442.3083.1
96.442.4083.1
96.442.5083.1
96.442.6083.1
96.442.7083.1
96.442.8083.1

RST 20i4

Cable assemblies

Cable 4 x 1.5 mm2; 16 A

Connection cables male – free end

250/400V
black

Cable

PVC cableÖlflex Classic 100
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.442.1084.1
96.442.2084.1
96.442.3084.1
96.442.4084.1
96.442.5084.1
96.442.6084.1
96.442.7084.1
96.442.8084.1

RST® CLASSIC = GN/YE
1 = BK 1
2 = BK 2
3 = BK 34-pole cables - one pole is not configured

139

RST 20i4

Distribution units
RST compact distribution unit
Dimensions

104 x 162 x 57.2 mm

Pre-wired with

2.5 mm2

Fitted as required with

M25 device connectors 4-pole

Mounting option

Yes

Color
n black

Circuit diagram

4

4

4

4

Input
1, RST20i4

Outputs
3, RST20i4

Part No.
99.911.0000.7

Outputs
4, RST20i4
5, RST20i4
7, RST20i4

Part No.
99.935.0000.7
99.916.0000.7
99.936.0000.7

RST multiple distribution unit
Dimensions

112 x 154 x 94 mm

Pre-wired with

2.5 mm2

Fitted as required with

M25 device connectors 4-poleFuse

6.3 or 10A can be integratedColor
n blackn blackn black

Circuit diagram
4

4

4

4

4

4

4

4

Input
1, RST20i4
1, RST20i4
1, RST20i4

Detailed information about the distribution units available in section "Compact/Multiple distribution units"

140

RST® CLASSIC

RST 20i4

141

RST 20i5

142

RST 20i5

General power applications, switching functions,power/dimming signals and low voltage

Application example

GeneralFour variations are available forapplications up to 250/400 V (forexample mains, switching functions,a version to combine power anddimming signals), as well as a version
for low-voltage applications up to
50/120 V.

RST® CLASSICAll connectors are mechanicallycoded. This means that only
associated pairs of male and female
can be connected with the correct
polarity. You therefore have thesecurity of a clear separation ofdifferent applications without having
to redo any incorrect connections.
The color of the connectors indicatesthe links that belong together.

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

Name
Connector

Distribution units

Deviceconnectors

Cable
assemblies

Description
1 x cable entry
2 x cable entry
RST compact distribution unit/
multi-distribution unit

Connection
style
Screw
Crimp
Screw
Spring clamp

MechanicalcodingStrain relief
housing

Connection points
per pole

yes

1

yes

1

preassembled
preassembled
preassembled

250V

, N, 3, 2, 1

L, N,
,D1, D2

light graypreassembled
preassembled
preassembled

preassembled
preassembled
preassembled

black

250/400V 250/400V ~50/-120V
1,2,3,
4,5

turquoise light blue

N,E,1,2,3

1,2,3,4,5

yellow

signalbrownü ü ü ü ü üü ü ü ü ü ü

onrequestonrequestIndividual distribution box
M16 device connector,
modular, straightM16 device connector,
modular, angled 7°
M25 device connector,
standard
M20 device connector,
standard
M20 device connector,
modular, straightM25 device connector,
modular, angled
Connection cableMale – Free end
Connection cable
Female – Free end
Extension cableMale – Female

250/400V

on
requestonrequestonrequestonrequestonrequestonrequestonrequestonrequestonrequestonrequestü ü ü üüü ü ü üüü ü ü ü ü üü ü ü üüü ü ü üüü ü ü üüü ü ü üüü ü ü üüü ü ü ü
ü143

RST 20i5

Connectors, straightfor cables Ø 6 – 10 mm and 10 – 14 mm

Female connector
Unmounted with cable gland.
Crimp contacts separately available under
Accessories.
See the Technical Data for sheath and insulation
strip lengths.

Application

CodingCable diameter in mm

, N, 3,2, 1

250/400V

L, , N,D1, D2
1, 2, 3, 4, 5

~50/-120V

6 – 10
10 – 14
6 – 10
10 –14
6 – 10
10 –14

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Colorlight grayblack
light grayblack
turquoiselight blue

Part No.

Part No.

96.051.4053.0
96.051.4053.1
96.051.4153.0
96.051.4153.1
96.051.4053.6
96.051.4153.6
96.051.4053.9
96.051.4153.9

96.151.0053.0
96.151.0053.1
96.151.0153.0
96.151.0153.1
96.151.0053.6
96.151.0153.6
96.151.0053.9
96.151.0153.9

N, E, 1, 2, 3

6 – 10yellow

96.051.4053.2

1, 2, 3, 4, 5

6 – 10
10 –14signalbrown

96.051.4051.4
96.051.4151.4

96.151.0051.4
96.151.0151.4

Contacts separately under Accessories, see following pages.

Male connector
Unmounted with cable gland and locking device.
Crimp contacts separately available under
Accessories.
See the Technical Data for sheath and insulation
strip lengths.

Application

CodingCable diameter in mm

, N, 3,2, 1

250/400V

L, , N,D1, D2
1, 2, 3, 4, 5

~50/-120V

1)

10 – 14
6 – 10
10 –14
6 – 10
10 –14turquoiselight blue

with crimp connection

Wire
rigid
fine-stranded
stranded
Locking device

Wirefine-stranded
Locking device

mm20.75 – 4.0
without ferrules
yes

mm2
0.75 – 4.0
yesPart No.

Part No.

96.052.4053.0
96.052.4053.1
96.052.4153.0
96.052.4153.1
96.052.4053.6
96.052.4153.6
96.052.4053.9
96.052.4153.9

96.152.0053.0
96.152.0053.1
96.152.0153.0
96.152.0153.1
96.152.0053.6
96.152.0153.6
96.152.0053.9
96.152.0153.9

N, E, 1, 2, 3

6 – 10yellow

96.052.4053.2

1, 2, 3, 4, 5

6 – 10
10 –14signalbrown

96.052.4051.4
96.052.4151.4

With wire protection available on request

144

6 – 10Color

light grayblack
light grayblackwith screw connection1)

96.152.0051.4
96.152.0151.4

Contacts separately under Accessories, see following pages.

RST 20i5

Connectors, angled 90°

for cables Ø 6 – 10 mm and 10 – 14 mm

Female connector
Unmounted with cable gland.
90° angle.
See the Technical Data for sheath andinsulation strip length as well as the ferrules
to be used.

CodingCable diameter in mm

, N, 3,2, 1

250/400V

L, , N,D1, D2
1, 2, 3, 4, 5

~50/-120V

1, 2, 3, 4, 5

6 – 10
10 – 14
6 – 10
10 –14
6 – 10
10 –14
6 – 10
10 –14

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Colorlight grayblack
light grayblack
turquoiselight blue
signalbrown

Part No.

Part No.

96.053.4053.0
96.053.4053.1
96.053.4153.0
96.053.4153.1
96.053.4053.6
96.053.4153.6
96.053.4053.9
96.053.4153.9
96.053.4051.4
96.053.4151.4

96.153.0053.0
96.153.0053.1
96.153.0153.0
96.153.0153.1
96.153.0053.6
96.153.0153.6
96.153.0053.9
96.153.0153.9
96.153.0051.4
96.153.0151.4

RST® CLASSIC

Application

with screw connection1)

Contacts separately under Accessories, see following pages.

Male connector
Unmounted with cable gland and locking
device.
90° angle.
See the Technical Data for sheath and insulation strip length as well as the ferrules
to be used.

Application

CodingCable diameter in mm

, N, 3,2, 1

250/400V

L, , N,D1, D2
1, 2, 3, 4, 5

~50/-120V

1, 2, 3, 4, 5

6 – 10
10 – 14
6 – 10
10 –14
6 – 10
10 –14
6 – 10
10 –14Colorlight grayblack
light grayblack
turquoiselight blue
signalbrown

with screw connection1)

with crimp connection

Wire
rigid
fine-stranded
stranded
Locking device

Wirefine-stranded
Locking device

mm20.75 – 4.0
without ferrules
yes

mm2
0.75 – 4.0
yesPart No.

Part No.

96.054.4053.0
96.054.4053.1
96.054.4153.0
96.054.4153.1
96.054.4053.6
96.054.4153.6
96.054.4053.9
96.054.4153.9
96.054.4051.4
96.054.4151.4

96.154.0053.0
96.154.0053.1
96.154.0153.0
96.154.0153.1
96.154.0053.6
96.154.0153.6
96.154.0053.9
96.154.0153.9
96.154.0051.4
96.154.0151.4
Contacts separately under Accessories, see following pages.

1)With wire protection available on request

145

RST 20i5

Connectors, straightfor cable Ø 13 – 18 mm

Female connector
Unmounted with cable gland.
Crimp contacts separately available under
Accessories.
See the Technical Data for sheath and insulation
strip lengths.

Application

250/400V~50/-120V

CodingCable diameter in mmwith screw connection1)

with crimp connection

Wire
rigid
fine-stranded
strandedWire
fine-stranded

mm2

mm2
0.75 – 4.0

0.75 – 4.0
without ferrules

Color

Part No.

Part No.

96.051.4553.0
96.051.4553.1

96.151.0553.0
96.151.0553.1

, N, 3,2, 1

13 – 18

light grayblack

L, , N,D1, D213 – 18

turquoise

96.051.4553.6

96.151.0553.6

1, 2, 3, 4, 5

13 – 18

light blue

96.051.4553.9

96.151.0553.9

N, E, 1, 2, 3

13 – 18

yellow

96.051.4553.2

13 – 18

signalbrown

96.051.4551.4

1, 2, 3, 4, 5

96.151.0551.4

Contacts separately under Accessories, see following pages.

Male connector
Unmounted with cable gland and locking device.
Crimp contacts separately available under
Accessories.
See the Technical Data for sheath and insulation
strip lengths.

Application

250/400V~50/-120V

CodingCable diameter in mm

Colorwith screw connection1)

with crimp connection

Wire
rigid
fine-stranded
stranded
Locking device

Wirefine-stranded
Locking device

mm20.75 – 4.0
without ferrules
yes

mm2
0.75 – 4.0
yesPart No.

Part No.

96.052.4553.0
96.052.4553.1

96.152.0553.0
96.152.0553.1

, N, 3,2, 1

13 – 18

light grayblack

L, , N,D1, D213 – 18

turquoise

96.052.4553.6

96.152.0553.6

1, 2, 3, 4, 5

13 – 18

light blue

96.052.4553.9

96.152.0553.9

N, E, 1, 2, 3

13 – 18

yellow

96.052.4553.2

13 – 18

signalbrown

96.052.4551.4

1, 2, 3, 4, 5

96.152.0551.4

Contacts separately under Accessories, see following pages.

1)With wire protection available on request

146

RST 20i5

Splitter connector, straightfor cables Ø 6 – 10 mm and 10 – 14 mm

Female connector
Unmounted with cable glands.
See Technical Data for sheath and insulation strip
lengths.

with screw connection1)

Application

CodingCable diameter in mm

, N, 3,2, 1

250/400V

L, , N,D1, D2
1, 2, 3, 4, 5

~50/-120V

1, 2, 3, 4, 5

6 – 10
10 – 14
6 – 10
10 –14
6 – 10
10 –14
6 – 10
10 –14mm20.75 – 1.5
without ferrules

Colorlight grayblack
light grayblack
turquoiselight blue
signalbrown

Part No.

96.051.4253.0
96.051.4253.1
96.051.4353.0
96.051.4353.1
96.051.4253.6
96.051.4353.6
96.051.4253.9
96.051.4353.9
96.051.4251.4
96.051.4351.4

RST® CLASSIC

Wire
rigid
fine-stranded
stranded

Mounting plate for splitter connectors
Colorn grayn black

1)

Part No.
01.006.1553.0
01.006.1553.1

With wire protection available on request

147

RST 20i5

M25 device connector
straight, standard

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from outside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.
For spacer rings for unlocking the device
connetor, see Accessories.

Application

Coding250/400V~50/-120V

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules1
M25 x 1.5
outsideColor

mm20.75 – 4.0
1
M25 x 1.5
outsideContacts separately under Accessories, see following pages.

Part No.

Part No.

, N, 3, 2, 1

light grayblack

96.051.5053.0
96.051.5053.1

96.151.1053.0
96.151.1053.1

L, , N, D1, D2

turquoise

96.051.5053.6

96.151.1053.6

1, 2, 3, 4, 5

light blue

96.051.5053.9

96.151.1053.9

N, E, 1, 2, 3

signal brown

1, 2, 3, 4, 5yellow

96.151.1053.2
96.051.5051.4

96.151.1051.4

Male connector
Correct positioning guaranteed due to flattened
thread. With locking device.
Fastening with screws from outside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

250/400V~50/-120V

148

CodingColorwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M25 x 1.5
outsideyes

mm20.75 – 4.0
1
M25 x 1.5
outsideyes

Contacts separately under Accessories, see following pages.

Part No.

Part No.

, N, 3, 2, 1

light grayblack

96.052.5053.0
96.052.5053.1

96.152.1053.0
96.152.1053.1

L, , N, D1, D2

turquoise

96.052.5053.6

96.152.1053.6

1, 2, 3, 4, 5

light blue

96.052.5053.9

96.152.1053.9

N, E, 1, 2, 3

signal brown

1, 2, 3, 4, 5yellow

96.152.1053.2
96.052.5051.4

96.152.1051.4

RST 20i5

M20 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Crimp contacts separately available under
Accessories.
See the Technical Data for sheath and insulation strip
lengths.

Coding250/400V~50/-120V

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideColor

mm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

, N, 3, 2, 1

light grayblack

96.051.6053.0
96.051.6053.1

96.151.2053.0
96.151.2053.1

L, , N, D1, D2

turquoise

96.051.6053.6

96.151.2053.6

1, 2, 3, 4, 5

light blue

96.051.6053.9

96.151.2053.9

1, 2, 3, 4, 5

signal brown

96.051.6051.4

96.151.2051.4

RST® CLASSIC

Application

with screw connection

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. With locking device.
Fastening with screws from inside.
Crimp contacts separately available under
Accessories.
See the Technical Data for sheath and insulation
strip lengths.

Application

250/400V~50/-120V

CodingColorwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideyes

mm20.75 – 4.0
1
M20 x 1.5
insideyesPart No.

Part No.

, N, 3, 2, 1

light grayblack

96.052.6053.0
96.052.6053.1

96.152.2053.0
96.152.2053.1

L, , N, D1, D2

turquoise

96.052.6053.6

96.152.2053.6

1, 2, 3, 4, 5

light blue

96.052.6053.9

96.152.2053.9

1, 2, 3, 4, 5

signal brown

96.052.6051.4

96.152.2051.4
Contacts separately under Accessories, see following pages.

149

RST 20i5

M16 device connector
straight, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

Coding250/400V~50/-120V

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules1
M16 x 1.5
insideColor

mm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

, N, 3, 2, 1

light grayblack

96.051.6153.0
96.051.6153.1

96.151.2153.0
96.151.2153.1

L, , N, D1, D2

turquoise

96.051.6153.6

96.151.2153.6

1, 2, 3, 4, 5

light blue

96.051.6153.9

96.151.2153.9

1, 2, 3, 4, 5

signal brown

96.051.6151.4

96.151.2151.4

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. With locking device.
Fastening with screws from inside.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

250/400V~50/-120V

CodingColorwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M16 x 1.5
insideyes

mm20.75 – 4.0
1
M16 x 1.5
insideyesPart No.

Part No.

, N, 3, 2, 1

light grayblack

96.052.6153.0
96.052.6153.1

96.152.2153.0
96.152.2153.1

L, , N, D1, D2

turquoise

96.052.6153.6

96.152.2153.6

1, 2, 3, 4, 5

light blue

96.052.6153.9

96.152.2153.9

1, 2, 3, 4, 5

signal brown

96.052.6151.4

96.152.2151.4
Contacts separately under Accessories, see following pages.

150

RST 20i5

M16 device connector
angled 7°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 7°, thread M16.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Coding250/400V~50/-120V

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules1
M16 x 1.5
insideColor

mm20.75 – 4.0
1
M16 x 1.5
insidePart No.

Part No.

, N, 3, 2, 1

light grayblack

96.055.6153.0
96.055.6153.1

96.155.2153.0
96.155.2153.1

L, , N, D1, D2

turquoise

96.055.6153.6

96.155.2153.6

1, 2, 3, 4, 5

light blue

96.055.6153.9

96.155.2153.9

1, 2, 3, 4, 5

signal brown

96.055.6151.4

96.155.2151.4

RST® CLASSIC

Application

with screw connection

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. With locking device.
Fastening with screws from inside.
Angled 7°, thread M16.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

250/400V~50/-120V

CodingColorwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M16 x 1.5
insideyes

mm20.75 – 4.0
1
M16 x 1.5
insideyesPart No.

Part No.

, N, 3, 2, 1

light grayblack

96.056.6153.0
96.056.6153.1

96.156.2153.0
96.156.2153.1

L, , N, D1, D2

turquoise

96.056.6153.6

96.156.2153.6

1, 2, 3, 4, 5

light blue

96.056.6153.9

96.156.2153.9

1, 2, 3, 4, 5

signal brown

96.056.6151.4

96.156.2151.4
Contacts separately under Accessories, see following pages.

151

RST 20i5

M20 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 90°, thread M20.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

Coding250/400V~50/-120V

with screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideColor

mm20.75 – 4.0
1
M20 x 1.5
insidePart No.

Part No.

, N, 3, 2, 1

light grayblack

96.053.6053.0
96.053.6053.1

96.153.2053.0
96.153.2053.1

L, , N, D1, D2

turquoise

96.053.6053.6

96.153.2053.6

1, 2, 3, 4, 5

light blue

96.053.6053.9

96.153.2053.9

1, 2, 3, 4, 5

signal brown

96.053.6051.4

96.153.2051.4

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. With locking device.
Fastening with screws from inside.
Angled 90°, thread M20.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

250/400V~50/-120V

CodingColorwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules
1
M20 x 1.5
insideyes

mm20.75 – 4.0
1
M20 x 1.5
insideyesPart No.

Part No.

, N, 3, 2, 1

light grayblack

96.054.6053.0
96.054.6053.1

96.154.2053.0
96.154.2053.1

L, , N, D1, D2

turquoise

96.054.6053.6

96.154.2053.6

1, 2, 3, 4, 5

light blue

96.054.6053.9

96.154.2053.9

1, 2, 3, 4, 5

signal brown

96.054.6051.4

96.154.2051.4
Contacts separately under Accessories, see following pages.

152

RST 20i5

M25 device connector
angled 90°, modular

Female connector
Correct positioning guaranteed due to flattened
thread. Fastening with screws from inside.
Angled 90°, thread M25.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Coding250/400V~50/-120V

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGlandWirefine-stranded
Term. poles
ThreadGlandmm20.75 – 4.0
without ferrules1
M25 x 1.5
insideColor

mm20.75 – 4.0
1
M25 x 1.5
insidePart No.

Part No.

, N, 3, 2, 1

light grayblack

96.053.6253.0
96.053.6253.1

96.153.2253.0
96.153.2253.1

L, , N, D1, D2

turquoise

96.053.6253.6

96.153.2253.6

1, 2, 3, 4, 5

light blue

96.053.6253.9

96.153.2253.9

1, 2, 3, 4, 5

signal brown

96.053.6251.4

96.153.2251.4

RST® CLASSIC

Application

with screw connection

Contacts separately under Accessories, see following pages.

Male connector
Correct positioning guaranteed due to flattened
thread. With locking device.
Fastening with screws from inside.
Angled 90°, thread M25.
Crimp contacts separately available under
Accessories.
See the Technical Data for insulation strip lengths.

Application

250/400V~50/-120V

CodingColorwith screw connection

with crimp connection

Wire
rigid
fine-stranded
strandedTerm. poles
ThreadGland
Locking device

Wirefine-stranded
Term. poles
ThreadGland
Locking device

mm20.75 – 4.0
without ferrules1
M25 x 1.5
insideyes

mm20.75 – 4.0
1
M25 x 1.5
insideyesPart No.

Part No.

, N, 3, 2, 1

light grayblack

96.054.6253.0
96.054.6253.1

96.154.2253.0
96.154.2253.1

L, , N, D1, D2

turquoise

96.054.6253.6

96.154.2253.6

1, 2, 3, 4, 5

light blue

96.054.6253.9

96.154.2253.9

1, 2, 3, 4, 5

signal brown

96.054.6251.4

96.154.2251.4
Contacts separately under Accessories, see following pages.

153

RST 20i5

Cable assemblies

Cable 5 x 1.5 mm2; 16 A
Rated values

Pull relief

with gland nut

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

black

Wire strip length(open cable end)

9 mm

Color handle shell

black

Connection cables female – male

250/400V
black = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-freePart No.

Part No.

1
2
3
4
5
6
7
8

96.452.1000.1
96.452.2000.1
96.452.3000.1
96.452.4000.1
96.452.5000.1
96.452.6000.1
96.452.7000.1
96.452.8000.1

96.452.1000.6
96.452.2000.6
96.452.3000.6
96.452.4000.6
96.452.5000.6
96.452.6000.6
96.452.7000.6
96.452.8000.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.452.1030.1
96.452.2030.1
96.452.3030.1
96.452.4030.1
96.452.5030.1
96.452.6030.1
96.452.7030.1
96.452.8030.1

96.452.1030.6
96.452.2030.6
96.452.3030.6
96.452.4030.6
96.452.5030.6
96.452.6030.6
96.452.7030.6
96.452.8030.6

Length m

Part No.

1
2
3
4
5
6
7
8

96.452.1050.1
96.452.2050.1
96.452.3050.1
96.452.4050.1
96.452.5050.1
96.452.6050.1
96.452.7050.1
96.452.8050.1

250/400V
black = GN/YE
N = BU
1 = BN
2 = BK
3 = GY

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

Other cable lengths, other codings upon request154

 = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length mConnection cables female – free end

Cable

250V
turquoise

250V
turquoise = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.452.1003.1
96.452.2003.1
96.452.3003.1
96.452.4003.1
96.452.5003.1
96.452.6003.1
96.452.7003.1
96.452.8003.1

96.452.1003.6
96.452.2003.6
96.452.3003.6
96.452.4003.6
96.452.5003.6
96.452.6003.6
96.452.7003.6
96.452.8003.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.452.1033.1
96.452.2033.1
96.452.3033.1
96.452.4033.1
96.452.5033.1
96.452.6033.1
96.452.7033.1
96.452.8033.1

96.452.1033.6
96.452.2033.6
96.452.3033.6
96.452.4033.6
96.452.5033.6
96.452.6033.6
96.452.7033.6
96.452.8033.6

Length m

Part No.

1
2
3
4
5
6
7
8

96.452.1053.1
96.452.2053.1
96.452.3053.1
96.452.4053.1
96.452.5053.1
96.452.6053.1
96.452.7053.1
96.452.8053.1

RST 20i5

Cable assemblies

Cable 5 x 1.5 mm2; 16 A

250/400V
black = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

250V
turquoise = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.452.1004.1
96.452.2004.1
96.452.3004.1
96.452.4004.1
96.452.5004.1
96.452.6004.1
96.452.7004.1
96.452.8004.1

96.452.1004.6
96.452.2004.6
96.452.3004.6
96.452.4004.6
96.452.5004.6
96.452.6004.6
96.452.7004.6
96.452.8004.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.452.1034.1
96.452.2034.1
96.452.3034.1
96.452.4034.1
96.452.5034.1
96.452.6034.1
96.452.7034.1
96.452.8034.1

96.452.1034.6
96.452.2034.6
96.452.3034.6
96.452.4034.6
96.452.5034.6
96.452.6034.6
96.452.7034.6
96.452.8034.6

Length m

Part No.

1
2
3
4
5
6
7
8

96.452.1054.1
96.452.2054.1
96.452.3054.1
96.452.4054.1
96.452.5054.1
96.452.6054.1
96.452.7054.1
96.452.8054.1

RST® CLASSIC

Connection cables male – free end

155

RST 20i5

Cable assemblies

Cable 5 x 2.5 mm2; 20 A
Rated values
Wire ends

Pull relief(open cable end)

with gland nut

ultrason. weldedInterlockintegrated

Sheath strip length (open cable end)

35 mm

Color cable

black

Wire strip length

9 mm

Color handle shell

black(open cable end)

Connection cables female – male

250/400V
black

250V
turquoise = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.453.1000.1
96.453.2000.1
96.453.3000.1
96.453.4000.1
96.453.5000.1
96.453.6000.1
96.453.7000.1
96.453.8000.1

96.453.1000.6
96.453.2000.6
96.453.3000.6
96.453.4000.6
96.453.5000.6
96.453.6000.6
96.453.7000.6
96.453.8000.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.453.1030.1
96.453.2030.1
96.453.3030.1
96.453.4030.1
96.453.5030.1
96.453.6030.1
96.453.7030.1
96.453.8030.1

96.453.1030.6
96.453.2030.6
96.453.3030.6
96.453.4030.6
96.453.5030.6
96.453.6030.6
96.453.7030.6
96.453.8030.6

Length m

Part No.

1
2
3
4
5
6
7
8

96.453.1050.1
96.453.2050.1
96.453.3050.1
96.453.4050.1
96.453.5050.1
96.453.6050.1
96.453.7050.1
96.453.8050.1

Connection cables female – free end

250/400V
black = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

Other cable lengths, other codings upon request156

 = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

250V
turquoise = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.453.1003.1
96.453.2003.1
96.453.3003.1
96.453.4003.1
96.453.5003.1
96.453.6003.1
96.453.7003.1
96.453.8003.1

96.453.1003.6
96.453.2003.6
96.453.3003.6
96.453.4003.6
96.453.5003.6
96.453.6003.6
96.453.7003.6
96.453.8003.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.453.1033.1
96.453.2033.1
96.453.3033.1
96.453.4033.1
96.453.5033.1
96.453.6033.1
96.453.7033.1
96.453.8033.1

96.453.1033.6
96.453.2033.6
96.453.3033.6
96.453.4033.6
96.453.5033.6
96.453.6033.6
96.453.7033.6
96.453.8033.6

Length m

Part No.

1
2
3
4
5
6
7
8

96.453.1053.1
96.453.2053.1
96.453.3053.1
96.453.4053.1
96.453.5053.1
96.453.6053.1
96.453.7053.1
96.453.8053.1

RST 20i5

Cable assemblies

Cable 5 x 2.5 mm2; 20 A

250/400V
black = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-Fenhanced version
halogen-free

250V
turquoise = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.453.1004.1
96.453.2004.1
96.453.3004.1
96.453.4004.1
96.453.5004.1
96.453.6004.1
96.453.7004.1
96.453.8004.1

96.453.1004.6
96.453.2004.6
96.453.3004.6
96.453.4004.6
96.453.5004.6
96.453.6004.6
96.453.7004.6
96.453.8004.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.453.1034.1
96.453.2034.1
96.453.3034.1
96.453.4034.1
96.453.5034.1
96.453.6034.1
96.453.7034.1
96.453.8034.1

96.453.1034.6
96.453.2034.6
96.453.3034.6
96.453.4034.6
96.453.5034.6
96.453.6034.6
96.453.7034.6
96.453.8034.6

Length m

Part No.

1
2
3
4
5
6
7
8

96.453.1054.1
96.453.2054.1
96.453.3054.1
96.453.4054.1
96.453.5054.1
96.453.6054.1
96.453.7054.1
96.453.8054.1

RST® CLASSIC

Connection cables male – free end

157

RST 20i5

Cable assemblies

Cable 5 x 2.5 mm2; 20 A (Power 5-pole)
Rated values

Pull relief

with gland nut

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cablegray

Wire strip length(open cable end)

9 mm

Color handle shell

black

Connection cables female – male

250/400V
black

Cable

Cable
Ölflex Classic 110
containing halogen

 = GN/YE
N = BK4
1 = BK1
2 = BK2
3 = BK3

Length m

Part No.

1
2
3
4
5
6
7
8

96.453.1080.1
96.453.2080.1
96.453.3080.1
96.453.4080.1
96.453.5080.1
96.453.6080.1
96.453.7080.1
96.453.8080.1

Connection cables female – free end

250/400V
black = GN/YE
N = BK4
1 = BK1
2 = BK2
3 = BK3

Cable

Cable
Ölflex Classic 110
containing halogen

Other cable lengths, other codings upon request

158

Length m

Part No.

1
2
3
4
5
6
7
8

96.453.1083.1
96.453.2083.1
96.453.3083.1
96.453.4083.1
96.453.5083.1
96.453.6083.1
96.453.7083.1
96.453.8083.1

RST 20i5

Cable assemblies

Cable 5 x 2.5 mm2; 20 A (Power 5-pole)

Connection cables male – free end

250/400V
black

Cable

Cable
Ölflex Classic 110
containing halogen

Length m

Part No.

1
2
3
4
5
6
7
8

96.453.1084.1
96.453.2084.1
96.453.3084.1
96.453.4084.1
96.453.5084.1
96.453.6084.1
96.453.7084.1
96.453.8084.1

RST® CLASSIC = GN/YE
N = BK4
1 = BK1
2 = BK2
3 = BK3

159

RST 20i5

Cable assemblies

Cable 5 x 4.0 mm2; 20 A
Rated values

Pull relief

with gland nut

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

black

Wire strip length(open cable end)

9 mm

Color handle shell

black

Connection cables female – male

250/400V
black = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

250V
turquoise = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.454.1000.1
96.454.2000.1
96.454.3000.1
96.454.4000.1
96.454.5000.1
96.454.6000.1
96.454.7000.1
96.454.8000.1

96.454.1000.6
96.454.2000.6
96.454.3000.6
96.454.4000.6
96.454.5000.6
96.454.6000.6
96.454.7000.6
96.454.8000.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.454.1030.1
96.454.2030.1
96.454.3030.1
96.454.4030.1
96.454.5030.1
96.454.6030.1
96.454.7030.1
96.454.8030.1

96.454.1030.6
96.454.2030.6
96.454.3030.6
96.454.4030.6
96.454.5030.6
96.454.6030.6
96.454.7030.6
96.454.8030.6

250/400V
black

250V
turquoise

Connection cables female – free end

 = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Other cable lengths, other codings upon request160

 = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.454.1003.1
96.454.2003.1
96.454.3003.1
96.454.4003.1
96.454.5003.1
96.454.6003.1
96.454.7003.1
96.454.8003.1

96.454.1003.6
96.454.2003.6
96.454.3003.6
96.454.4003.6
96.454.5003.6
96.454.6003.6
96.454.7003.6
96.454.8003.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.454.1033.1
96.454.2033.1
96.454.3033.1
96.454.4033.1
96.454.5033.1
96.454.6033.1
96.454.7033.1
96.454.8033.1

96.454.1033.6
96.454.2033.6
96.454.3033.6
96.454.4033.6
96.454.5033.6
96.454.6033.6
96.454.7033.6
96.454.8033.6

RST 20i5

Cable assemblies

Cable 5 x 4.0 mm2; 20 A

Connection cables male – free end

 = GN/YE
N = BU
1 = BN
2 = BK
3 = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

250V
turquoise = GN/YE
N = BUL = BN
D1 = GY
D2 = BK

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.454.1004.1
96.454.2004.1
96.454.3004.1
96.454.4004.1
96.454.5004.1
96.454.6004.1
96.454.7004.1
96.454.8004.1

96.454.1004.6
96.454.2004.6
96.454.3004.6
96.454.4004.6
96.454.5004.6
96.454.6004.6
96.454.7004.6
96.454.8004.6

Length m

Part No.

Part No.

1
2
3
4
5
6
7
8

96.454.1034.1
96.454.2034.1
96.454.3034.1
96.454.4034.1
96.454.5034.1
96.454.6034.1
96.454.7034.1
96.454.8034.1

96.454.1034.6
96.454.2034.6
96.454.3034.6
96.454.4034.6
96.454.5034.6
96.454.6034.6
96.454.7034.6
96.454.8034.6

RST® CLASSIC

250/400V
black

161

RST 20i5

Distribution units
RST compact distribution unit

3 outputs routing 230 /400V, 20 A

RST 20i5 Coding Color black

Dimensions

104 x 162 x 57.2 mm

Mounting option

Yes

Pre-wired with

2.5 mm2Colorn light greyn black

Circuit diagram

5

5

5

5

Input
1
1

Outputs
3
3

Part No.
upon request
96.050.0153.1

RST multiple distribution unit

Fitted as required with

M25 device connector 2- up to 5-pole

Dimensions

104 x 162 x 96 mm

Fuse

6.3 or 10A can be integrated

Pre-wired with

2.5 mm2Colorn blackn black

Input
11

Outputs
7
5

Part No.
upon request
96.050.2153.1

Detailed information about the distribution units available in section ”Compact/Multiple distribution units“

162

RST® CLASSIC

RST 20i5

163

RST 25i5
20i5

164

RST 25i5

Solar applications up to 32 A for single-phase supply withthree-phase power monitoring or three-phase supply

Application example

General

RST® CLASSIC

The system has been specially
adapted to the requirements of solar
technology.
The connectors can be loaded withmax. 32 A and are used for singlephase supply with power monitoringor three-phase supply.
Special distribution boxes are used
to bundle the electrical power of up
to 6 inverters and thus complete thesystem.
These connectors have their own
mechanical coding. This means that
only associated pairs of male andfemale can be connected with thecorrect polarity. This ensures a clear
separation from the connectors of theother product series.

Features:■ Fast mounting through easy handling■ UV-resistant■ Rated current up to 32 A (at 6.0 mm2)
■ Cross-sections up to 6 mm2■ Degree of protection IP66/68 (3m; 2h) /69

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

MechanicalcodingName

Description

Connection
style

Strain relief
housing

Connection points
per pole

Connector

1 x cable entry

Screw

yes

1

Distribution units

Distribution box
RST RAN Solar
Distribution box
RST Solar

Deviceconnectors

M25 device connector,
Standard

Cable
assemblies

Connection cableMale – Free end
Connection cable
Female – Free end
Extension cableMale – Femalepreassembled
preassembled
preassembled

preassembled
preassembled
preassembled

preassembled
preassembled
preassembled

250/400V
L, N, , 1, 2

concrete gray

ü
ü
ü
ü
ü
ü
ü

165

RST 25i5

Connectors, straightfor cables Ø 10 – 14 mm and 13 – 18 mm

Female connector

Application

Codingwith screw connection
for cables Ø 13 –18 mm

Wire
solid
fine-stranded

Wire
solid
fine-stranded

Color

L, N, ,1, 2

250/400V

with screw connection
for cables Ø 10 –14 mm

concrete gray/
black

mm2
up to 4.0

Part No.

without ferrules

Cross-section

96.051.4154.3

4 mm

2

mm2
up to 4.0
up to 6.0

Part No.

without ferrules

Cross-section

96.051.4554.3

4 mm2

99.575.0000.7

6 mm2Male connector

Application

250/400V

166

CodingColor

L, N, ,1, 2

concrete gray/blackwith screw connection
for cables Ø 10 –14 mmwith screw connection
for cables Ø 13 –18 mm

Wire
solid
fine-stranded

Wire
solid
fine-stranded

mm2
up to 4.0

Part No.

96.052.4154.3

without ferrules

Cross-section

4 mm

2

mm2
up to 4.0
up to 6.0

Part No.

without ferrules

Cross-section

96.052.4554.3

4 mm2

99.576.0000.7

6 mm2

RST 25i5

M25 device connector
straight, standard

Female connector
With sealing option
For spacer rings forunlocking the device
connector, see
Accessories.
with screw connection
Wire
mm2
solid
up to 4.0
up to 6.0
fine-stranded
Application

CodingColor

L, N, ,1, 2

250/400V

concrete gray/black

Part No.

without ferrules
Cross-section

96.051.5054.3

4 mm2

99.577.0000.7

6 mm2Male connector
With sealing option

Application

250/400V

CodingColor
L, N, ,1, 2

concrete gray/black

Part No.

without ferrules
Cross-section

96.052.5054.3

4 mm2

99.578.0000.7

6 mm2

RST® CLASSIC

with screw connection
Wire
mm2
solid
up to 4.0
up to 6.0
fine-stranded

167

RST 25i5

Cable assemblies

Cable 5 x 4.0 mm2; 25 A
Rated values

Pull relief

with gland nut

Wire ends(open cable end)

ultrason. weldedInterlockintegrated

Sheath strip length(open cable end)

35 mm

Color cable

black

Wire strip length(open cable end)

9 mm

Color handle shell

black

Connection cables female – male

250/400V
concrete gray/black = GN/YE
N = BU
1 = BN
2 = BKL = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.854.1000.3
96.854.1500.3
96.854.2000.3
96.854.2500.3
96.854.3000.3
96.854.3500.3
96.854.4000.3

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.854.1030.3
96.854.1530.3
96.854.2030.3
96.854.2530.3
96.854.3030.3
96.854.3530.3
96.854.4030.3

Connection cables female – free end

250/400V
concrete gray/black = GN/YE
N = BU
1 = BN
2 = BKL = GYCable

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

168

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.854.1003.3
96.854.1503.3
96.854.2003.3
96.854.2503.3
96.854.3003.3
96.854.3503.3
96.854.4003.3

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.854.1033.3
96.854.1533.3
96.854.2033.3
96.854.2533.3
96.854.3033.3
96.854.3533.3
96.854.4033.3

Cable diameter 14.3 mm ± 0.2
According to VDE 0281/T5 and
VDE 0288/T4

Cable diameter 17.0 mm ± 0.3
According to VDE 0281/T5 and
VDE 0288/T4

RST 25i5

Cable assemblies

Cable 5 x 4.0 mm2; 25 A

Connection cables male – free end

250/400V
concrete gray/black = GN/YE
N = BU
1 = BN
2 = BKL = GY

PVC cable
H05VV-F
containing halogen

Cable

Rubber-sheathed cable
H07RN-F
containing halogen

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.854.1004.3
96.854.1504.3
96.854.2004.3
96.854.2504.3
96.854.3004.3
96.854.3504.3
96.854.4004.3

Length m

Part No.

1.0
1.5
2.0
2.5
3.0
3.5
4.0

96.854.1034.3
96.854.1534.3
96.854.2034.3
96.854.2534.3
96.854.3034.3
96.854.3534.3
96.854.4034.3

Cable diameter 14.3 mm ± 0.2
According to VDE 0281/T5 and
VDE 0288/T4

Cable diameter 17.0 mm ± 0.3
According to VDE 0281/T5 and
VDE 0288/T4

RST® CLASSIC

Cable

169

RST 20i6

Also on our
You Tube channel

RST® CLASSIC

The new RST20i6 and i7More poles for greater demands
Following the current trend, Wieland Electric continues to expand its RST® product range, presenting a 6- and7-pole variant for the first time.
A total of three codings ensure both mechanical and color differentiation of the various circuits. To increasesafety, a distinction is also drawn between applications with and without protective earth. The compact
connectors with key data 250/400V; 600V UL/CSA, 20A, IP 66 / 68 (3m; 2h) / 69 offer high modularity andadaptability to the requirements of the application. Connectors are available in straight or angled versions, aswell as for all common cable diameters. The range even includes connectors with 2 cable inputs for throughwiring. Both screw and crimp fittings are offered as the connection system.
As an interface to electrical devices, the system offers straight and angled adapters for all standard housing
bores (for M16, M20, M25). All devices can therefore easily to converted to RST without changing tools.

170

RST 20i6

Combination of one-phase systems (network) with signals
and emergency light

Application example

GeneralMulti-functionality requires a higher
number of poles.
The system components, rated for up
to 20 A, can accommodate cables of
up to a maximum 2.5 mm² and areavailable with screw or crimp fittings.
The 6-pole variant is designed specifically for dimming emergency lights.

RST® CLASSIC

Different codings within the RST
series allow a mechanical and visual
separation from other circuits.

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

250/400V
L, N, , 1, 2, Ls

Mechanical coding

Name

Description

Connection system

Strain-relief housing

Connection points
per pole

1x cable guide

Screw
Crimp

yes

1

2x cable guide

Screw
Crimp fitting

yes

1Connector

Distributors

RST compact splitter/
multi-splitter

Cable assembliesüü
on request

Individual distribution box

Device connectors

turquoiseon request

Device connector M16, modular,
straight

1

Device connector M16, modular,
7° angled1

Device connector M25, standard

1

Device connector M25, modular,
straight

1

Device connector M20, modular,
straight

1

Device connector M20, modular,
angled1

Device connector M25, modular,
angled

1

ü
ü
ü
ü
ü
ü

Device connector cableMale – free end

pre-assembled

pre-assembled

pre-assembled

on request

Connection cable
Female – free end

pre-assembled

pre-assembled

pre-assembled

on request

Extension cableMale – female

pre-assembled

pre-assembled

pre-assembled

on request

171

RST 20i6

Connector, straight
For cables Ø 6 - 10 mm and 10 - 14 mm

Female connector
Unmounted with screwed cable gland.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

L, N, ,1, 2, Ls

250/400V

6 - 10
10 - 14Color

turquoise

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.061.4053.6

9L.061.4053.6

96.161.0053.6

9L.161.0053.6

96.061.4153.6

9L.061.4153.6

96.161.0153.6

9L.161.0153.6

Male connector
Unmounted with screwed cable gland and lock.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

Application

250/400V

1)

CodingØ cable mm

L, N, ,1, 2, Ls

6 - 10
10 - 14Color

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.062.4053.6

on request

96.162.0053.6

on request

96.062.4153.6

on request

96.162.0153.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

172

mm2
0.75-2.5

RST 20i6

Connector, angled 90°
For cables Ø 6 - 10 mm and 10 - 14 mm

Female connector
Unmounted with screwed cable gland, 90° angle.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

L, N, ,1, 2, Ls

250/400V

6 - 10
10 - 14Color

turquoise

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.063.4053.6

9L.063.4053.6

96.161.0053.6

9L.163.0053.6

96.063.4153.6

9L.063.4153.6

96.163.0153.6

9L.163.0153.6

RST® CLASSIC

With screw connection

Male connector
Unmounted with screwed cable gland and lock.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

Application

250/400V

1)

CodingØ cable mm

L, N, ,1, 2, Ls

6 - 10
10 - 14Color

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.064.4053.6

on request

96.164.0053.6

on request

96.064.4153.6

on request

96.164.0153.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

173

RST 20i6

Connector, straight
For cables Ø 13 - 18 mm

Female connector
Unmounted with screwed cable gland.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

L, N, ,1, 2, Ls

250/400V

13 - 18

Color

turquoise

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.061.4553.6

9L.061.4553.6

96.161.0553.6

9L.161.0553.6

Male connector
Unmounted with screwed cable gland and lock.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

Application

250/400V

1)

CodingØ cable mm

L, N, ,1, 2, Ls

13 - 18

Color

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.062.4553.6

on request

96.162.0553.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

174

mm2
0.75-2.5

RST 20i6

Connector with double connection, straight
For cables Ø 6 - 10 mm and 10 - 14 mm

Female connector
Unmounted with screwed cable gland.
With or without contact seal.
For stripping lengths, refer to Technical
Specifications.

With screw connection
CablesRigid
Fine stranded
Stranded

250/400V

CodingØ cable mm

L, N, ,1, 2, Ls

6 - 10
10 - 14Color

turquoise

0.2 - 1.5 (without ferrules)

Part No.

Part No.

Without contact seal

With contact seal 1)

96.061.4253.6

on request

96.061.4353.6

on request

RST® CLASSIC

Application

mm2

Mounting plate for splitter connectors
Colorn light grayn black

1)

Part No.
01.006.1553.0
01.006.1553.1

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

175

RST 20i6

Device connector M25
straight, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingColor

L, N, ,1, 2, Ls

250/400V

turquoise

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.061.6253.6

9L.061.6253.6

96.161.2253.6

9L.161.2253.6

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColor

L, N, ,1, 2, Ls

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.062.6253.6

9L.062.6253.6

96.162.2253.6

9L.162.2253.6

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

176

mm2
0.75-2.5

RST 20i6

Device connector M20
straight, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Sstranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

CodingColor

L, N, ,1, 2, Ls

250/400V

turquoisePart No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.061.6053.6

9L.061.6053.6

96.161.2053.6

9L.161.2053.6

RST® CLASSIC

Application

mm20.75-2.5

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColor

L, N, ,1, 2, Ls

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.062.6053.6

9L.062.6053.6

96.162.2053.6

9L.162.2053.6

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

177

RST 20i6

Device connector M16
straight, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingColor

L, N, ,1, 2, Ls

250/400V

turquoise

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.061.6153.6

9L.061.6153.6

96.161.2153.6

9L.161.2153.6

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColor

L, N, ,1, 2, Ls

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.062.6153.6

9L.062.6153.6

96.162.2153.6

9L.162.2253.6

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

178

mm2
0.75-2.5

RST 20i6

Device connector M16
angled 7°, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

CodingColor

L, N, ,1, 2, Ls

250/400V

turquoisePart No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.065.6153.6

Upon request

96.165.2153.6

Upon request

RST® CLASSIC

Application

mm20.75-2.5

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColor

L, N, ,1, 2, Ls

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.066.6153.6

Upon request

96.166.2153.6

Upon request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

179

RST 20i6

Device connector M20
angled 90°, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingColor

L, N, ,1, 2, Ls

250/400V

turquoise

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.063.6053.6

on request

96.163.2053.6

on request

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColor

L, N, ,1, 2, Ls

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.064.6053.6

on request

96.164.2053.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

180

mm2
0.75-2.5

RST 20i6

Device connector M25
angled 90°, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

CodingColor

L, N, ,1, 2, Ls

250/400V

turquoisePart No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.063.6253.6

on request

96.163.2253.6

on request

RST® CLASSIC

Application

mm20.75-2.5

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColor

L, N, ,1, 2, Ls

turquoiseWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

96.064.6253.6

on request

96.164.2253.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

181

RST 20i7

Also on our
You Tube channel

RST® CLASSIC

182

RST 20i7

Combination of multi-phase systems (network) with signals,
protection class II

Application example

GeneralMulti-functionality requires a higher
number of poles.
The system components, rated for up
to 20 A, can accommodate cables of
up to a maximum 2.5 mm² and areavailable with screw or crimp fittings.
The 7-pole variants are available witha total of 3 codings.

RST® CLASSIC

Different codings within the RST
series allow a mechanical and visual
separation from other circuits.

CodingApplication

For daily updates visit the website at
http://eshop.wieland-electric.com.
Assembly instructions and other technical information can be foundin the Technical Data or in eShop.

Name

Description

Connection
systemStrain-relief
housing

Connection points
per pole

1x cable guide

Screw
Crimp

yes

1

2x cable guide

Screw
Crimp

yes

1

1, 2, 3, 4/N, 5, 6, 

1, 2, 3, 4/N, 5, 6, 7

L, N, , 1, 2, 3, 4

light blue

turquoise

ü
ü

ü
ü

ü
ü

ü
ü

Individual distribution box

on request

on request

on request

on request

Device connector M16,
modular, straight

ü
ü

ü
ü

ü
ü

ü
ü

ü
ü
ü
ü

ü
ü
ü
ü

ü
ü
ü
ü

ü
ü
ü
ü

RST compact splitter/
multi-splitter

Device connector M25,
standard
Device connector M25,
modular, straight
Device connector M20,
modular, straight
Device connector M20,
modular, angled
Device connector M25,
modular, angled

Cable assemblies

250/400V

black

Device connector M16,
modular, 7° angled

Device connectors

250/400V

light grayConnector

Distributors

Mechanicalcoding250/400V

Device connector cableMale – free end

pre-assembled

pre-assembled

pre-assembled

on request

on request

on request

on request

Connection cable
Female – free end

pre-assembled

pre-assembled

pre-assembled

on request

on request

on request

on request

Extension cableMale – female

pre-assembled

pre-assembled

pre-assembled

on request

on request

on request

on request

183

RST 20i7

Connector, straight

For cables Ø 6 - 10 mm and 10 - 14 mm

Female connector
Unmounted with screwed cable gland.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

1, 2, 3, 4/N,
5, 6, 250/400V

1, 2, 3, 4/N,
5, 6, 7
L, N, ,1, 2, 3, 4

6 – 10
10 – 14
6 – 10
10-14
6 – 10
10-14

Color

light grayblack
light grayblack
light blue
turquoisePart No.

Part No.

Without contact seal

With contact seal

96.071.4053.0
96.071.4053.1
96.071.4153.0
96.071.4153.1
96.071.4053.9
96.071.4153.9
96.071.4053.6
96.071.4153.6

9L.071.4053.0
9L.071.4053.1
9L.071.4153.0
9L.071.4153.1
9L.071.4053.9
9L.071.4153.9
9L.071.4053.6
9L.071.4153.6

1)mm2
0.75-2.5

Part No.

Part No.

Without contact seal

With contact seal 1)

96.171.0053.0
96.171.0053.1
96.171.0153.0
96.171.0153.1
96.171.0053.9
96.171.0153.9
96.171.0053.6
96.171.0153.6

9L.171.0053.0
9L.171.0053.1
9L.171.0153.0
9L.171.0153.1
9L.171.0053.9
9L.171.0153.9
9L.171.0053.6
9L.171.0153.6

Male connector
Unmounted with screwed cable gland and lock.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Multi-stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

1, 2, 3, 4/N,
5, 6, 250/400V

1, 2, 3, 4/N,
5, 6, 7
L, N, ,1, 2, 3, 4

1)

6 – 10
10 – 14
6 – 10
10-14
6 – 10
10-14

Color

light grayblack
light grayblack
light blue
turquoisePart No.

Part No.

Without contact seal

With contact seal

96.072.4053.0
96.072.4053.1
96.072.4153.0
96.072.4153.1
96.072.4053.9
96.072.4153.9
96.072.4053.6
96.072.4153.6

on request
on request
on request
on request
on request
on request
on request
on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

184

1)

mm2
0.75-2.5

Part No.

Part No.

Without contact seal

With contact seal 1)

96.172.0053.0
96.172.0053.1
96.172.0153.0
96.172.0153.1
96.172.0053.9
96.172.0153.9
96.172.0053.6
96.172.0153.6

on request
on request
on request
on request
on request
on request
on request
on request

RST 20i7

Connector, straight

For cables Ø 6 - 10 mm and 10 - 14 mm

Female connector
Unmounted with screwed cable gland. 90° angle
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Multi-stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

1, 2, 3, 4/N,
5, 6, 250/400V

1, 2, 3, 4/N,
5, 6, 7
L, N, ,1, 2, 3, 4

6 – 10
10 – 14
6 – 10
10-14
6 – 10
10-14

Color

light grayblack
light grayblack
light blue
turquoisePart No.

Part No.

Without contact seal

With contact seal

96.073.4053.0
96.073.4053.1
96.073.4153.0
96.073.4153.1
96.073.4053.9
96.073.4153.9
96.073.4053.6
96.073.4153.6

9L.073.4053.0
9L.073.4053.1
9L.073.4153.0
9L.073.4153.1
9L.073.4053.9
9L.073.4153.9
9L.073.4053.6
9L.073.4153.6

1)mm2
0.75-2.5

Part No.

Part No.

Without contact seal

With contact seal 1)

96.173.0053.0
96.173.0053.1
96.173.0153.0
96.173.0153.1
96.173.0053.9
96.173.0153.9
96.173.0053.6
96.173.0153.6

9L.173.0053.0
9L.173.0053.1
9L.173.0153.0
9L.173.0153.1
9L.173.0053.9
9L.173.0153.9
9L.173.0053.6
9L.173.0153.6

RST® CLASSIC

With screw connection

Male connector
Unmounted with screwed cable gland and lock.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Multi-stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

CodingØ cable mm

1, 2, 3, 4/N,
5, 6, 250/400V

1, 2, 3, 4/N,
5, 6, 7
L, N, ,1, 2, 3, 4

1)

6 – 10
10 – 14
6 – 10
10-14
6 – 10
10-14

Color

light grayblack
light grayblack
light blue
turquoisePart No.

Part No.

Without contact seal

With contact seal

96.074.4053.0
96.074.4053.1
96.074.4153.0
96.074.4153.1
96.074.4053.9
96.074.4153.9
96.074.4053.6
96.074.4153.6

on request
on request
on request
on request
on request
on request
on request
on request

1)mm2
0.75-2.5

Part No.

Part No.

Without contact seal

With contact seal 1)

96.174.0053.0
96.174.0053.1
96.174.0153.0
96.174.0153.1
96.174.0053.9
96.174.0153.9
96.174.0053.6
96.174.0153.6

on request
on request
on request
on request
on request
on request
on request
on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

185

RST 20i7

Connector, straight

For cables Ø 13 - 18 mm

Female connector
Unmounted with screwed cable gland.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

250/400V

CodingØ cable mm

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, 13 – 18

light grayblack

96.071.4553.0
96.071.4553.1

9L.071.4553.0
9L.071.4553.0

96.171.0553.0
96.171.0553.1

9L.171.0553.0
9L.171.0553.1

1, 2, 3, 4/N,
5, 6, 7

13 – 18

light blue

96.071.4553.9

9L.071.4553.9

96.171.0553.9

9L.171.0553.9

L, N, ,1, 2, 3, 4

13 – 18

turquoise

96.071.4553.6

9L.071.4553.6

96.171.0553.6

9L.171.0553.6

Male connector
Unmounted with screwed cable gland and lock.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

Application

250/400V

1)

CodingØ cable mm

Color

With screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, 13 – 18

light grayblack

96.072.4553.0
96.072.4553.1

on request
on request

96.172.0553.0
96.172.0553.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7

13 – 18

light blue

96.072.4553.9

on request

96.172.0553.9

on request

L, N, ,1, 2, 3, 4

13 – 18

turquoise

96.072.4553.6

on request

96.172.0553.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

186

mm2
0.75-2.5

RST 20i7

Connector with double connection, straight
For cables Ø 6 - 10 mm and 10 - 14 mm

Female connector
Unmounted with screwed cable gland.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical Specifications.

With screw connection
CablesRigid
Fine stranded
Stranded

CodingØ cable mm

1, 2, 3, 4/N,
5, 6, 250/400V

1, 2, 3, 4/N,
5, 6, 7
L, N, ,1, 2, 3, 4

6 – 10
10 – 14
6 – 10
10-14
6 – 10
10-14

Color

light grayblack
light grayblack
light blue
turquoise

0.2-1.5 (without ferrules)

Part No.

Part No.

Without contact seal

With contact seal 1)

96.071.4253.0
96.071.4253.1
96.071.4353.0
96.071.4353.1
96.071.4253.9
96.071.4353.9
96.071.4253.6
96.071.4353.6

on request
on request
on request
on request
on request
on request
on request
on request

RST® CLASSIC

Application

mm2

Mounting plate for splitter connectors
Colorn light grayn black

1)

Part No.
01.006.1553.0
01.006.1553.1

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

187

RST 20i7

Device connector M25
straight, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

Coding250/400V

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.071.6253.0
96.071.6253.1

9L.071.6253.0
9L.071.6253.1

96.171.2253.0
96.171.2253.1

9L.171.2253.0
9L.171.2253.1

1, 2, 3, 4/N,
5, 6, 7light blue

96.071.6253.9

9L.071.6253.9

96.171.2253.9

9L.171.2253.9

L, N, ,1, 2, 3, 4

turquoise

96.071.6253.6

9L.071.6253.6

96.171.2253.6

9L.171.2253.6

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColorWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.072.6253.0
96.072.6253.1

9L.072.6253.0
9L.072.6253.1

96.172.2253.0
96.172.2253.1

9L.172.2253.0
9L.172.2253.1

1, 2, 3, 4/N,
5, 6, 7light blue

96.072.6253.9

9L.072.6253.9

96.172.2253.9

9L.172.2253.9

L, N, ,1, 2, 3, 4

turquoise

96.072.6253.6

9L.072.6253.6

96.172.2253.6

9L.172.2253.6

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

188

mm2
0.75-2.5

RST 20i7

Device connector M20
straight, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

Coding250/400V

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.071.6053.0
96.071.6053.1

9L.071.6053.0
9L.071.6053.1

96.171.2053.0
96.171.2053.1

9L.171.2053.0
9L.171.2053.1

1, 2, 3, 4/N,
5, 6, 7light blue

96.071.6053.9

9L.071.6053.9

96.171.2053.9

9L.171.2053.9

L, N, ,1, 2, 3, 4

turquoise

96.071.6053.6

9L.071.6053.6

96.171.2053.6

9L.171.2053.6

RST® CLASSIC

With screw connection

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColorWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.072.6053.0
96.072.6053.1

9L.072.6053.0
9L.072.6053.1

96.172.2053.0
96.172.2053.1

9L.172.2053.0
9L.172.2053.1

1, 2, 3, 4/N,
5, 6, 7light blue

96.072.6053.9

9L.072.6053.9

96.172.2053.9

9L.172.2053.9

L, N, ,1, 2, 3, 4

turquoise

96.072.6053.6

9L.072.6053.6

96.172.2053.6

9L.172.2053.6

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

189

RST 20i7

Device connector M16
straight, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

Coding250/400V

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.071.6153.0
96.071.6153.1

9L.071.6153.0
9L.071.6153.1

96.171.2153.0
96.171.2153.1

9L.171.2153.0
9L.171.2153.1

1, 2, 3, 4/N,
5, 6, 7light blue

96.071.6153.9

9L.071.6153.9

96.171.2153.9

9L.171.2153.9

L, N, ,1, 2, 3, 4

turquoise

96.071.6153.6

9L.071.6153.6

96.171.2153.6

9L.171.2153.6

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColorWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.072.6153.0
96.072.6153.1

9L.072.6153.0
9L.072.6153.1

96.172.2153.0
96.172.2153.1

9L.172.2153.0
9L.172.2153.1

1, 2, 3, 4/N,
5, 6, 7light blue

96.072.6153.9

9L.072.6153.9

96.172.2153.9

9L.172.2153.9

L, N, ,1, 2, 3, 4

turquoise

96.072.6153.6

9L.072.6153.6

96.172.2153.6

9L.172.2153.6

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

190

mm2
0.75-2.5

RST 20i7

Device connector M16
angled 7°, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

Coding250/400V

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.075.6153.0
96.075.6153.1

on request
on request

96.175.2153.0
96.175.2153.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7light blue

96.075.6153.9

on request

96.175.2153.9

on request

L, N, ,1, 2, 3, 4

turquoise

96.075.6153.6

on request

96.175.2153.6

on request

RST® CLASSIC

With screw connection

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColorWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.076.6153.0
96.076.6153.1

on request
on request

96.176.2153.0
96.176.2153.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7light blue

96.076.6153.9

on request

96.176.2153.9

on request

L, N, ,1, 2, 3, 4

turquoise

96.076.6153.6

on request

96.176.2153.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

191

RST 20i7

Device connector M20
angled 90°, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With screw connection

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

Coding250/400V

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.073.6053.0
96.073.6053.1

on request
on request

96.173.2053.0
96.173.2053.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7light blue

96.073.6053.9

on request

96.173.2053.9

on request

L, N, ,1, 2, 3, 4

turquoise

96.073.6053.6

on request

96.173.2053.6

on request

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColorWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.074.6053.0
96.074.6053.1

on request
on request

96.174.2053.0
96.174.2053.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7light blue

96.074.6053.9

on request

96.174.2053.9

on request

L, N, ,1, 2, 3, 4

turquoise

96.074.6053.6

on request

96.174.2053.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

192

mm2
0.75-2.5

RST 20i7

Device connector M25
angled 90°, modular

Female connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

With crimp connection

Cablesmm
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

2

Application

Coding250/400V

Color

mm2
0.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.073.6253.0
96.073.6253.1

on request
on request

96.173.2253.0
96.173.2253.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7light blue

96.073.6253.9

on request

96.173.2253.9

on request

L, N, ,1, 2, 3, 4

turquoise

96.073.6253.6

on request

96.173.2253.6

on request

RST® CLASSIC

With screw connection

Male connector
Position fixing guaranteed by flattening thethread. Screwed from inside.
With or without contact seal.
Crimp contacts separate, Accessories.
For stripping lengths, refer to Technical
Specifications.

Application

250/400V

1)

CodingColorWith screw connection

With crimp connection

Cablesmm2
Rigid
Fine stranded
0.2 - 2.5
Stranded
Cables with 2.5 mm² only without ferrules

CablesFine stranded

mm20.75-2.5

Part No.

Part No.

Part No.

Part No.

Without contact seal

With contact seal 1)

Without contact seal

With contact seal 1)

1, 2, 3, 4/N,
5, 6, light grayblack

96.074.6253.0
96.074.6253.1

on request
on request

96.174.2253.0
96.174.2253.1

on request
on request

1, 2, 3, 4/N,
5, 6, 7light blue

96.074.6253.9

on request

96.174.2253.9

on request

L, N, ,1, 2, 3, 4

turquoise

96.074.6253.6

on request

96.174.2253.6

on request

When using connectors with contact sealing, use only one connector with contact sealing – either male or female connector

193

Accessories

Cover pieces for 2-/3-pole

for female

For the safe closure of female and male connectors.
With mounting strap for snapping onto plug connectors and device connectors

not captive against lossColorn light grayn black

for female
Part No.
Z5.564.4553.0
Z5.564.4553.1

for malePart No.
05.564.4453.0
05.564.4453.1

for female
Part No.
99.413.6205.2
99.414.6205.2

for malePart No.
99.415.6205.2
99.416.6205.2

for malefor female

captive against lossColorn light grayn black

for maleCrimp contacts for 2-/3-pole
Female contacts

Male contacts

194

Name
Female crimp contact
Female crimp contact
Female crimp contact
Female crimp contact

Marking1
unmarked1
unmarked(groove) mm2
0.75 – 1.0
1.5
2.5
4.0

Part No.
02.122.9000.002.122.9100.002.122.9200.0
02.122.9300.0

Male crimp contact
Male crimp contact
Male crimp contact
Male crimp contact1
unmarked1
unmarked

0.75 – 1.0
1.5
2.5
4.0

05.544.7800.0
05.544.7900.0
05.544.8000.0
05.545.4600.0

Accessories

Cover pieces for 4-/5-pole

for female

For the safe closure of female and male connectors.
With mounting strap for snapping onto plug connectors and device connectors

not captive against lossColorn light grayn black

for female
Part No.
Z5.565.9853.0
Z5.565.9853.1

for malePart No.
05.565.9953.0
05.565.9953.1

for female
Part No.
99.529.0000.7
99.530.0000.7

for malePart No.
99.531.0000.7
99.532.0000.7

for malefor female

captive against lossColorn light grayn black

RST® CLASSIC

for maleCrimp contacts for 4-/5-pole
Female contact

Male contact

Name
Female contact
Female contact
Female contact
Female contact

MarkingNone
12
3(groove) mm2
0.75 – 1.0
1.5
2.5
4.0

Part No.
02.125.5521.8
02.125.5621.8
02.125.5721.8
02.125.5821.8

Male contact
Male contact
Male contact
Male contact

None
1
2
3

0.75 – 1.0
1.5
2.5
4.0

05.545.0021.8
05.545.0121.8
05.545.0221.8
05.545.0321.8

195

Accessories

Cover pieces for 6-/7-pole

for female

For the safe closure of female and male connectors.
With mounting strap for snapping onto plug connectors and device connectors

not captive against lossColorn black

for female
Part No.
Z5.569.5253.1

for malePart No.
Z5.569.5353.1

for female
Part No.
99.589.0000.7

for malePart No.
99.591.0000.7

for malefor female

captive against lossColorn black

for maleCrimp contacts for 6-/7-pole
Female contact

Male contact

196

Name
Female contact
Female contact
Female contact

MarkingNone
12(groove) mm2
0.75 – 1.0
1.5
2.5

Part No.
02.127.1121.8
02.127.1221.8
02.127.1321.8

Male contact
Male contact
Male contact

None
1
2

0.75 – 1.0
1.5
2.5

05.546.3921.8
05.546.4021.8
05.546.4121.8

Accessories

Crimping tool
Name
Crimping tool incl. system kit
Crimping die B
Contact positioner

Part No.
95.101.0800.005.502.2100.005.502.3600.0

Name
Unlocking toolPart No.
05.502.3500.0

Unlocking tool

RST® CLASSIC

for crimp contacts

Socket frame for device connectors M25
straight (female)Protection rating:

IP 44

RST approval:

2PfG1915, EN61535

Entry:

2- up to 5-poleColorn whitePart No.
99.400.9999.7

197

Accessories

Manual disconnect toolPoles

2- up to 5-pole

Retrofitting of plug connectors (female only)Colorn blackn concrete grayn leaves green

Part No.
05.564.8653.1
05.564.8653.3
05.564.8653.7

With the manual disconnect tool, only one button must be pressed to easily disconnect theconnections.
Also see the Mounting Instructions!

Manual disconnect tool

Cable

RST20i2, RST20i3

Retrofitting of pre-assembled cables

Modelshrinkage tube

Colorn blackn concrete grayn leaves green

Part No.
05.565.8653.1
05.565.8653.3
05.565.8653.7

With the manual disconnect tool, only one button must be pressed to easily
disconnect the connections.
Also see the Mounting Instructions!

Manual disconnect tool for 6-/7-poleName
Manual disconnect tool

Locking slide - Safety ClipPart No.
06.562.8753.0

for replacement need, delivery quantity 100 pieces
Colorn blackn concrete grayPart No.
05.583.2900.1
05.583.2900.3

Note: The locking devices are integrated in the according plug parts at the factory. They click
audibly when plugged in, confirming the safe connection. They are by default loosened witha screw driver or with the manual disconnect facility (can be ordered separately). In case ofexcessive tension on the connection these will loosen, however, to prevent hazards by wires
pulled out of the contacts. This safety mechanism will lead to wear or destroy the slider, whichshould be replaced after having been activated several times.

Spacer ring for device connector M25,
female connector 2- up to 5-pole
Manually actuatedfor replacement needScrewdriver actuatedColorn light grayn black

manually
actuatedwithscrewdriverPart No.
05.568.8853.0
05.568.8853.1

Part No.
05.566.5253.0
05.566.5253.1

A spacer ring makes it possible to unlock a connection at the device connector (female).

198

Accessories

Ferrule crimping tool

for termination points with spring clamp technology

Cable end sleeves

0.08 – 6.0 mm 2, AWG 28 – 10

Total length

174 mmSquare compression; releasable latch; compression adjustable

Name
Ferrule crimping tool

Cable end sleeves

Part No.
95.101.1300.0

for RST 20i3 spring clamp connectors
Insulating sleeve

Yes

SleevePolypropylene

for wires

Temperature resistance

up to 105 °C, tracking resistant

0.50 mm2

DIN 46228-E0,5-10

Tube

E-Cu, galvanically tin-plated

0.75 mm2

DIN 46228-E0,75-12

1.00 mm 2

DIN 46228-E1,0-12

1.50 mm 2

DIN 46228-E1,5-12

mm2
0.50
0.75
1.00
1.50

Color
white
gray
red
black

Part No.
06.600.3827.0
06.600.3727.0
06.600.3627.0
06.600.3927.0

12

mm

10

mm

Name
Cable end sleeves
Cable end sleeves
Cable end sleeves
Cable end sleeves

Screwdriveraccording to DIN 5264

for RST spring clamp connections
Blade
0.4 x 2.5 mm

Name
Screwdriver

Fastening cord

Part No.
06.502.4300.0

for cover pieces 2-/3-pole & 4-/5-polig

Colorn light grayPart No.
99.000.9950.6

199

RST® CLASSIC

Materials

Accessories

Sample kit RST 20i3

Contents:

getting to know

– Connector– Device connector– Cover pieces

Name
Sample set RST 20i3

Sample kit RST 20i5

Contents:

getting to know

Part No.
99.429.0000.0– Connector– Device connector– Cover pieces

Name
Sample kit RST 20i5

Sample kit RST 20i7

Contents:

getting to know

Part No.
99.430.0000.0– Connector– Device connector– Cover pieces

Name
Sample kit RST 20i7

Sample kit RST 20i2...i7
getting to know

Contents:

Part No.
99.696.0000.0– Connectors, including all codings– Device connectors– Pre-assembled cables– Distributors– Cover pieces

Name
Sample set RST 20i2...i7 complete kit

200

Part No.
99.431.0000.0

Accessories

getting to know

Contents:

1x X6.030.0153.1
1x X6.031.1053.0
1x X6.031.1053.1
1x X6.032.1053.0
1x X6.032.1053.1

Name
ATEX , IECEx RST 20i3

Sample set RST 20i5
getting to know

Contents:

Name
ATEX RST 20i5

Part No.
99.663.0000.0

1x X6.051.4153.0
1x X6.052.4153.0
1x X6.051.5053.1
1x X6.052.5053.0
Part No.
99.664.0000.0

RST® CLASSIC

Sample set RST 20i3

201

Technical data

Technical data RST® CLASSIC
RST 20i2/i3

RST 25i3

RST 20i4/i5

RST 25i5

RST 20i6/i7

Rated voltage

250/400 V

250 V

250/400 V

250/400 V

250/400V

Rated current

20 A

25 A
32 A

20 A

25 A
32 A

(with 6.0 mm2)
Number of poles

2- or 3-poles

3-poles4- or 5-poles

20 A(with 6.0 mm2)

(3 x 20 A; 4 x 5 A)
no defining of poles

5-poles6- or 7-poles

Operating temperature:-40° C to +100° C
H05VV cable max 70 °C, H07RN-F max. 60 °C, H07 RN-F enhanced 90 °C

Material:

Contact parts: brass, surface-treated
Housing parts: polyamide, halogen-free, V2
Sealing material: NBR

Regulations:

IEC 61535 (VDE 0606); DIN EN 61984 (VDE 0627); VDE 0110
IEC 60999: UL 2238; CSA: C22.2 No.182.2-M1987;
LR Type Approval System
2 PfG 1915

Pollution severity:

3 (when connected)

Degree of protection:

IP66 / 68 (3m; 2h) / 69, barrier seal optional at RST20i6/7
Pre-assembled cable as a shrink hose variant IP66/ 68 (3m; 2h)
The installation instructions must be observed (see page with installation instructions)

IK code:

IK 07 (2 Joule)

Plugging cycles:

100x without load and 50x under nominal load (cos = 0.6) as per IEC 61535
RST20i2/3 / RST25i3 provide up to 5,000 plugging cycles and RST20i4/5 / RST25i5 up
to 3,000 plugging cycles without load. After approx. 600 plugging cycles, however,the sealing should be checked and, if required, re-lubricated with a suitable lubricant(e.g. Berulub FR 43 UV).

Glow-wire test:

RST20i2-i5/RST25i3/i5: with 850° C, 30 s
RST20i6/i7: with 960° C, 30 s
for connectors, distribution units, cable assemblies and device connectors

Coding:Mechanical coding symbolized by color code. Color gray and black with the samemechanical coding. Other codings are optional.

Approvals:

VDE; TÜV Rheinland; LR; GL; DNV; RINA; BV; ATEX; IECEx; cULus; CSA**; UL*(observe conditions of acceptability)* without cable assembles in shrinkage tube technology and connectors with spring clamp technology** without cable assembles in shrinkage tube technology

You can find the direct assignment of approvals and part numbers in the internet in
the eShop under http://eshop.wieland-electric.com, or consult us.

Note:

Protection against shock generally guaranteed even when disconnected. Ground conductor leading. Connection to the live cablemust be with a female connector according to the regulations.
It is therefore not possible to have a ring circuit arrangement.
Only pluggable in the correct pole configuration; 1 pole cannot be connected.
Contacts protected against strain on the cable. All components can be interlocked.
A locking device is required for IEC 6153 approval.
DIN VDE 0606 T200 conformity does not automatically exclude the danger of confusion with third-party installation plug connector
systems! Installation plug connector systems are no substitute for national plug/outlet systems for domestic use.
IEC 60364-5-52 must be observed – see note under ”Electrical installations with increased degree of protection“.

202Technical data

Wire preparation
Sheath stripping and insulation removal lengths
RST 2- /3-pole
all lengths indicated in mm
Screw connection:

Connector
6 – 10 mm
10 – 14 mm

Connector
13 – 18 mm

Splitter connector, 3-polemax. 2 x 2.5 mm 2

Splitter connector, 2-polemax. 2 x 2.5 mm 2

Insulation strip length X =Spring clamp connection:

0.75 mm2

1.0 mm2

1.5 mm2

2.5 mm 2

4.0 mm2

6.0 mm2

AWG 12– 18

solid

8

8

8

8

8

8

–

fine-stranded

8

8

8

8

8

8

–

stranded

8

8

8

8

8

8

8

ultrasonically compressed

8

8

8

8

8

8

–

Conductor cross-section

Connector

Fine-stranded and stranded wires

Splitter connector

RST® CLASSIC

Screwdriver
PZ1
Rated torque:
0.8 – 1.0 Nm

Ferrules required
Insulation strip length X =Conductor cross-section

0.5 mm 2

0.75 mm2

1.0 mm2

1.5 mm2

2.5 mm 2

solid

14.5 + 1

14.5 + 1

14.5 + 1

14.5 + 1

14.5 + 1

fine-stranded

12.0 + 1

13.0 + 1

13.0 + 1

13.0 + 1

Ferrules according to DIN

46228-E0.5-10 46228-E0.75-12 46228-E1.0-12

stranded

13.0 + 1

46228-E0.75-12 46228-E1.0-12

Ferrules according to DIN
ultrasonically compressed

Crimp connection:

13.0 + 1

14.5 + 1

14.5 + 1

46228-E1.5-12

13.0 + 1
46228-E1.5-12

14.5 + 1

Connector 6 – 10 mm, 10 – 14 mm

14.5 + 1

Connector 13 –18 mm

Insulation strip length X =Conductor cross-section

0,75 mm 2

1,0 mm2

1,5 mm2

2,5 mm 2

4,0 mm2

fine-stranded

8.0 + 1

8.0 + 1

8.0 + 1

8.0 + 1

8.0 + 1203

Technical data

Wire preparation
Sheath stripping and insulation removal lengths
RST 4 /5-pole
all lengths indicated in mm
Screw connection:

Connector
6 – 10 mm
10 – 14 mm

Connector
13 – 18 mm

Splitter connector
max. 2 x 1.5 mm2

Insulation strip lengthh X =Screwdriver
PZ1
Rated torque:
0.5 – 0.7 Nm

Crimp connection:

0.75 mm2

1.0 mm2

1.5 mm2

2.5 mm 2

4.0 mm2

6.0 mm2

AWG 12 – 18

solid

8

8

8

8

8

8

–

fine-stranded

8

8

8

8

8

8

–

stranded

8

8

8

8

8

8

8

ultrasonically compressed

8

8

8

8

8

8

–

Conductor cross-section

Connector
6 – 10 mm
10 – 14 mm

Connector
13 – 18 mm

Insulation strip length X =204Conductor cross-section

0,75 mm 2

1,0 mm2

1,5 mm2

2,5 mm 2

4,0 mm2

fine-stranded

7.0 + 1

7.0 + 1

7.0 + 1

7.0 + 1

7.0 + 1

Technical data

Wire preparation
Sheath stripping and insulation removal lengths
RST 6 /7-pole
all lengths indicated in mm
Screw connection:

Connector
6 – 10 mm
10 – 14 mm

Connector
13 – 18 mm

Splitter connector
max. 2 x 1.5 mm2

Insulation strip lengthh X =Crimp connection:

Conductor cross-section

AWG 14– 20

0.2 mm 2

0.5 mm20.75 mm2

1.0 mm2

1.5 mm2

2.5 mm 2

solid

8*

8*

8*

8*

8*

8 **

8*

fine-stranded

8*

8*

8*

8*

8*

8 **

8 **

Connector
6 – 10 mm
10 – 14 mm

Connector
13 – 18 mm

RST® CLASSIC

Screwdriver
PZ1
Rated torque:
0.5 – 0.7 Nm

Insulation strip length X =Conductor cross-section

0.75 mm2

1.0 mm2

1.5 mm2

2.5 mm 2

AWG 14-20

fine-stranded

7.0 + 1

7.0 + 1

7.0 + 1

7.0 + 1

7.0 + 1205

Technical data

Derating curves
RST 20i3
Screw connection – spring clamp connection
Derating curve according to IEC 61984 Edition 2 dated 10/2008 paragraph 7.3.8
20

2.5 mm2
Spring clamp

2.5 mm2
Screw
connection

18

4.0 mm2
Screw connection

16

14

Current [A]

12

10

8

6

4

2

0

50

55

60

65

70

75

80

85

90

95

100

105

Ambient temperature [° C]

RST 25i3
Screw connection
Derating curve according to IEC 61984 Edition 2 dated 10/2008 paragraph 7.3.8

30

6.0 mm2
Screw connection

27.5

25

4.0 mm2
Screw connection

22.5

Current [A]

20

17.5

15

12.5

10

7.5

5

2.5

0

20

25

30

35

40

45

50

55

60

65

70

Ambient temperature [° C]

206

75

80

85

90

95

100

105

Technical data

Derating curves
RST 20i5
Screw connection – crimp connection
Derating curve according to IEC 61984 Edition 2 dated 10/2008 paragraph 7.3.8
4.0 mm2 crimp connection

20

2.5 mm2
Screw
connection

2.5 mm2
crimp connection

18

4.0 mm2
Screw connection

16

14

Current [A]

12

10

8

6

4

0

30

35

40

45

50

55

60

65

70

75

80

85

90

95

100

RST® CLASSIC

2

105

Ambient temperature [° C]

RST 25i5Screw connection
Derating curve according to IEC 61984 Edition 2 dated 10/2008 paragraph 7.3.8
6.0 mm2 Screw connection
32
30
28

4.0 mm2
Screw connection

26
24
22

Current [A]

20
18
16
14
12
10
8
6
4
2
0

20

25

30

35

40

45

50

55

60

65

70

Ambient temperature [° C]

75

80

85

90

95

100

105

207

Installation
instructions

Connectors 2- and 3-pole

Connect the wires (screw connection) ...

... and disconnect them (crimp connection)

Screw connection:

Tightening torque typicallytyp. 0.8 – 1.0 Nm

Close the connector ...

... and open it

Tightening
torque4.0 + 1,0 Nm

Lock the housing ...

... and unlock it

How to insert the (optional) manual disconnect tool into the connector(only possible for the female connector)
The manual disconnect tool can be used
as an alternative and enables disconnecting
without a tool.
The descriptions on this page merely serve as an overview.
For assembly and installation, only the installation instructions
supplied together with the products are binding

The corresponding installation instruction BA000104 canbe found online in the download section of the respective
product under: eshop.wieland-electric.com

208Installation
instructions

Device connections 2- and 3-pole
Installation of a standard system,
for M16 and M20 feed-throughInstallation of a standard system,
for M 25 feed-throughDimensions in mm

Dimensions in mm

Tightening
torque2 ... 2.5 Nm
D(mm)16.4 -0,2
20.4 -0,2
25.4 -0,2

d (mm)
15.0 -0,2
19.0 -0,2
23.9 -0,2

RST® CLASSIC

M16
M20
M25

Tightening
torque2 ... 2.5 Nm

Note:
Effectiveness of the protection against twisting can only
be guaranteed when the lower tolerance limit is ensured
for the diameter of the hole.

➀➁

Bending radius (for conductors)
Note the minimum bending radius for
conductors > 2.5 mm2. Pull forces on thecontact points can be avoided by proceeding
as follows::

Bend the wire as required
Cut the wire to length ➁Strip the cable and wires ➂➂The corresponding installation instruction BA000104 canbe found online in the download section of the respective
product under: eshop.wieland-electric.com

209Installation
instructions

Connectors 4- and 5-pole

Connect the wires (screw connection) ...

... and disconnect them (crimp connections

Screw connection:
Tightening
torque0.5 – 0.7 Nm

Close the connector ...

... and open it

Tightening torque
4.0 + 1,0 Nm

Lock the housing ...

... and unlock it

How to insert the (optional) manual disconnect tool into the connector(only possible for the female connector)

The manual disconnect tool can be used
as an alternative and enables disconnecting
without a tool.
The descriptions on this page merely serve as an overview.
For assembly and installation, only the installation instructions
supplied together with the products are binding

The corresponding installation instruction BA000104 canbe found online in the download section of the respective
product under: eshop.wieland-electric.com

210

Installation
instructions

Device connections 4- and 5-pole
Installation of a standard system,
for M16 and M20 feed-throughInstallation of a standard system,
for M25 feed-throughDimensions in mm

Dimensions in mm
max. 8 mm

max. 8 mmTightening torque2 … 2.5 Nm
D (mm)
16.4 -0,2
20.4 -0,2
25.4 -0,2

d (mm)
15.0 -0,2
19.0 -0,2
23.9 -0,2

RST®
RST®CLASSIC
CLASSIC

M16
M20
M25

Tightening torque2 … 2.5 Nm

Note:
Effectiveness of the protection against twisting can only
be guaranteed when the lower tolerance limit is ensured
for the diameter of the hole.

➀➁

Bending radius (for conductors)
Note the minimum bending radius for
conductors > 2.5 mm2. Pull forces on thecontact points can be avoided by proceeding
as follows::

Bend the wire as required
Cut the wire to length ➁Strip the cable and wires ➂➂The corresponding installation instruction BA000104 canbe found online in the download section of the respective
product under: eshop.wieland-electric.com

211Installation
instructions

Connectors 6- and 7-pole

Connect the wires (screw connection) ...

... and disconnect them (crimp connections

Screw connection:
Tightening
torquetyp. 0.5 Nm

Close the connector ...

... and open it
Tightening torquetyp. 4.0 + 1,0 Nm

Plugging and locking

Unlocking and separating

How to insert the (optional) manual disconnect tool into the connector(only possible for the female connector)

The manual disconnect tool can be used
as an alternative and enables disconnecting
without a tool.
The descriptions on this page merely serve as an overview.
For assembly and installation, only the installation instructions
supplied together with the products are binding

The corresponding installation instructions BA001155 and BA001156
can be found online in the download section of the respective productunder: eshop.wieland-electric.com

212

Installation
instructions

Device connections 6- and 7-pole
Housing installation with
M16, M20 and M25 feed-throughDimensions in mm

Tightening torquetyp. 2.5 … 3 Nm

D (mm)
16.4 -0,2
20.4 -0,2
25.4 -0,2

d (mm)
15.0 -0,2
19.0 -0,2
23.9-0,2

RST® CLASSIC

M16
M20
M25

The corresponding installation instructions BA001155 and BA001156 can be found online in the download section of therespective product under: eshop.wieland-electric.com

213

Distribution
RST 20i5units

214

Distribution units

Compact and multi-distribution units
for use in rough environments

GeneralThe pluggable distribution units playa major role in power distribution. In
their simplest function, they merely
have to provide branches in therequired locations. Practice shows,
however, that the requirements may
be much more complex.
Examples can be found in AC andDC wiring through distribution units
with microfuses up to boxes withintegrated safety outlets or switches.

Compact / multidistribution units

Application example

215

Distribution units

Compact and multi-distribution units
Flexibility according to the modular RST® principle

The highest level of flexibility!
Two housing variations are the basis:
a flat design with up to four slots, anda high design with a total of up to
eight slots. Unused slots are closed at
the factory.
The distribution units are equippedindividually with suitable device
connectors. These connectors
are available in various poleconfigurations, with mechanicalcoding and designs; they are wired tocustomer‘s requirements.

Depending on the application, you
can choose among 30 codings fromthe range of RST®CLASSIC and
RST®MINI. Mechanically codedmeans that only the matching
male and female connectors canbe plugged together. Thus you
can be sure that your different
applications are clearly distinguished– without having to rework incorrectconnections.The connector colors
signal the matching connections.
The standard power coding is an
exception. Here you can selectbetween black and gray.
These are compatible with one
another.

Overview of the standard
components:

RST16i2

RST16i3

RST16i4

RST16i5

RST20i2

RST20i3

RST20i4

RST20i5

RST25i3

250V
black orlight gray
L, N

250V
black orlight gray
L, N, PE

250/400V
black orlight gray1, 2 ,3, N, PE

250/400V
black orlight gray1, 2 ,3, N, PE

250V
black orlight gray
L, N

250V
black orlight gray
L, N, PE

250/400V
black orlight grayPE, 1, 2, 3

250/400V
black orlight grayPE, N, 3, 2,1

250V
concrete gray
L, N, PE

250/400V
light blue
1, 2

250/400V
leaf green
1, 2, PE

250/400V
leaf green
1, 2, PE

250V
turquoise
L, N, PE, 1, 2

250V
turquoise
L, N, PE, D1, D2

250/400V
pebble gray+, -250/400V
turquoise
D1, D2250/400V
light blue
1, 2, 3~50/-120V
signal brown
1, 2, 3, 4

250/400V
light blue
1, 2, 3

250/400V
light blue
1, 2, 3, 4, 5

~50/-120V
signal brown
1, 2, 3,4

250/400V
light blue
1, 2, 3, 4, 5

~50/-120V
signal brown
1, 2~50/-120V
signal brown
1, 2

250/400V
turquoise
D1, D2, PE~50/-120V
signal brown
1, 2, 3216

~50/-120V
signal brown
1, 2, 3, 4, 5

~50/-120V
signal brown
1, 2, PE

250/400V
yellow
N, E, 1, 2, 3

~50/-120V
signal brown
1, 2, 3, 4, 5

RST25i5

250/400V
concrete gray
L, N, PE, 1, 2

Distribution
RST 20i5units

Mounting
Four fixing clips on theoutside ensure easy
installation and safe
fixation.
At the bottom, there are
extra fixing holes for
attachment of a special
mounting plate.

UnlockingCompact / multidistribution units

All pluggable connections areprotected against accidentalloosening. This is guaranteed
by a locking facility integrated
during production. On plug-in,
the locking facility latches with
an audible click.
The connection is releasedusing a screwdriver.

Cover pieces
Cover pieces are required
for safely covering unused
outputs.
These are available either withor without protection against
loss.

Housing design: flat

Circuit diagram
A circuit diagram on the
housing cover provides
information about the internal
wiring.
The outputs are numberedfrom X1 to X8.

Housing design: high217Distribution
RST 20i5units

Compact distribution units with max. 4 slots
RST compact distribution unit

routing 3 outputs 230/400V, 20A

RST 20i5 coding Color black

Dimensions (W x L x H)

104 x 162 x 57.2 mm

Pre-wired with

2.5 mm2

Number of poles

5-poleMounting option

Yes

Color
n grayn black

Input
11

Outputs
3
3

Part No.
upon request
96.050.0153.1

Circuit diagram

5

5

5

5

RST compact distribution unit

routing 2 outputs 230/400V, 20A

RST 20i5 Coding Color black

Dimensions (W x L x H)

104 x 162 x 57.2 mm

Pre-wired with

2.5 mm2

Number of poles

5-poleMounting option

Yes

Color
n grayn black

Circuit diagram

Input
1
1

Outputs2
2

RST compact distribution unit

routing 1 output 230/400V, 20A

RST 20i5 coding Color black

Dimensions (W x L x H)

104 x 162 x 57.2 mm

1 output 230V, 20A

RST 20i3 coding Color black

Number of poles

5-/3-pole

Pre-wired with

2.5 mm2

Mounting option

Yes

Color
n grayn blackn blackn black

Circuit diagram

Pole marking
L1
L2
L3

Input
1
1
1
1

Outputs22
2
2

RST compact distribution unit

1 input 230/400V, 20A

RST 20i5 coding Color black

Dimensions (W x L x H)

104 x 162 x 57.2 mm

3 outputs 230V, 20A

RST 20i3 coding Color black

Number of poles

5-/3-pole

Pre-wired with

2.5 mm2

Mounting option

Yes

Color
n grayn black

Circuit diagram

218

5

L1

L3

L2

Pole marking
L1, L2, L3

Input
1
1

Outputs
3
3

Part No.
upon request
96.050.1153.1

Part No.
upon request
96.050.3153.1
96.050.4153.1
96.050.5153.1

Part No.
Upon request
96.050.6153.1

Distribution
RST 20i5units

AS-i distribution unit
3 outputs 230/400V, 20A

RST 20i4 coding Color brown

Dimensions (W x L x H)

104 x 162 x 57.2 mm

Pre-wired with

2.5 mm2

Number of poles

4-poleMounting option

Yes

Color
n grayn black

Circuit diagram

4

4

4

4

Mounting plate for example to fit on themesh cable tray
(see illustration below)

Input
1
1

Dimensions (W x L x H)

105 x 154 x 4.5 mm

Mounting option

Yes

Outputs
3
3

Part No.
upon request
96.040.0151.4

Part No.
G0.500.2041.5

Compact / multidistribution units

Distribution box AS-i / 24V

219

Distribution
RST 20i5units

Multi-distribution units with max. 8 slots
Multi-distribution unit 5-/3-pole,
1I/7O, 2x L1, L2, L3

Dimensions (W x L x H)

1, RST 20i5 coding black

outputs 230V, 20A

6, RST 20i3 coding blackColorn grayn black

Circuit diagram

Multi-distribution unit 5-/3-pole,
1I/3O, L1, L2, L3

Dimensions (W x L x H)

Multi-distribution unit 5-/3-pole,
1I/3O, L1, L2, L3

1, RST 20i5 coding black
3, RST 20i3 coding black

3, RST 20i3 coding black
10A, 5 x 20 mm

IP 65, 66, 67

including microfuse

Colorn grayn black

Distribution box
Power and AS-i / 24 V

Input power 230/400V, 20A
104 x 162 x 96 mm

4

4

4

5

5

5

5

Input
1
1

Outputs
3
3

Part No.
upon request
99.902.0000.7

Part No.
upon request
99.901.0000.71Outputs power 230/400V, 20A

3, RST 20i5 coding black

input AS-i/24V, 20A

1

outputs AS-i/24V, 20A

3, RST 20i4 coding brownColorn black
Circuit diagram

Outputs
4
4

1, RST 20i5 coding blackProtection type

220

Input
1
1

input 230/400V, 20A

104 x 162 x 96 mm

Part No.
upon request
96.050.7153.1

104 x 162 x 96 mm

outputs 230V, 20A

Dimensions (W x L x H)

Circuit diagram

Outputs
7
7

routing outputs 230/400V, 20A

outputs 230 V, with 3 integrated microfuse
holders up to 10 A

4

Input
1
1

Color
n grayn black

Circuit diagram

Dimensions (W x L x H)

104 x 162 x 96 mm

routing outputs 230/400V, 20A

Input
1

Outputs
3

Part No.
99.903.0000.7

Compact / multidistribution units

Distribution
RST 20i5units

221

Distribution
RST 20i5units

Multi-distribution units,
radio, halogen technology, LED technology
Switching output unit EnOcean 4-foldPower In-/Output
Outputs
Connection type

Rated voltage

230V AC / 20A connectors RST 20i3 codingblack
4
connector RST20i3, coding blackType
RC RST-0/4

Circuit diagram
X5
X1
X4

3

3

3

3

RC

3

230 V AC
6A (max. two of the LED/LV halogen
modules given below)
Protection type
IP 65, 66, 67, 68 (3m; 2h)Dimensions (length/width/height) 104/162/96 mm
Mounting option
4 elongated holes
Switching capacity

3Name
4 relay outputs, 1 feed-through wiring

Part No.
83.020.0505.0

X6
X2
X3

The EnOcean 4-fold switching output unit in IP68 surface housing for outdoor use features four 230V relays.
They can be programmed for 30 push button pairs. All electrical connections are pluggable.

Constant power supply unit, 350 mA DC
Power input (male connector)
230V AC/20A RST 20i3 coding black
Power output (female connector) 230V AC/20A RST 20i3 coding black
350mA DC/max. 12W RST 20i2 coding
Output LED (female connector)
brown

Protection type
IP 65, 66, 67, 68 (3m; 2h), 69
Ambient temperature-25 °C up to +55 °C
Dimensions (length/width/height) 104/162/96 mm
Mounting option
4 elongated holes
Electrical connections
pluggable with RST 20i2...20i3

Type
RST PSI 350/12 LED

Part No.
83.020.0902.0

Circuit diagram
X1

3

3

X2

I
2

X3

Constant power supply unit 350 mA for connecting LEDs.
Connections not used have to be closed.

Constant power supply unit, 700 mA DC
Power input (male connector)
230V AC/20A, RST 20i3 coding black
Power output (female connector) 230V AC/20A RST 20i3, coding black
700mA DC/max. 12W, RST 20i2 coding
Output LED (female connector)
brown

Type
RST PSI 700/12 LED

Circuit diagram
X1

3

Protection type
IP 65, 66, 67, 68 (3m; 2h), 69
Ambient temperature-25 °C up to +55 °C
Dimensions (length/width/height) 104/162/96 mm
Mounting option
4 elongated holes
Electrical connections
pluggable with RST 20i2...20i3

3Part No.
83.020.0903.0

X2

I
2

X3

Constant power supply unit 700 mA for connecting LEDs. Connections not used have to be closed.

Constant power supply unit, 12 V DC
Power input (male connector)
230V AC/20A RST 20i3, coding black
Power output (female connector) 230V AC/20A RST 20i3, coding black
12V DC/max. 12W RST 20i2, coding signal
Output LED (female connector)
brown

Type
RST PSU 12/12 LED

Circuit diagram
X1

3

Protection type
IP 65, 66, 67, 68 (3m; 2h), 69
Ambient temperature-25 °C up to +55 °C
Dimensions (length/width/height) 104/162/96 mm
Mounting option
4 elongated holes
Electrical connections
pluggable with RST 20i2...20i3

3

X2

U
2

222

X3

Constant voltage supply unit 12 V for connecting LEDs.
Connections not used have to be closed.

Part No.
83.020.0900.0

Distribution
RST 20i5units

Constant power supply unit, 24 V DC
power input (male connector)
230V AC/20A RST 20i3, coding black
power output (female connector) 230V AC/20A RST 20i3, coding black
24V DC/max. 12W RST20i2, coding signal
output LED (female connector)
brown

RST PSU 24/12 LED

Circuit diagram
X1

3

Protection type
IP 65, 66, 67, 68 (3m; 2h), 69
Ambient temperature-25 °C up to +55 °C
Dimensions (length/width/height) 104/162/96 mm
Mounting option
4 elongated holes
Electrical connections
pluggable with RST 20i2...20i3

3

83.020.0901.0

X2

U
2

X3

Constant voltage supply unit 24 V for connecting LEDs.
Connections not used have to be closed.

Transformer for low voltage halogen luminaires, 12 V AC Output LV halogen
Power input (male connector)
230 V AC/20 A RST 20i3, coding black
Power output (female connector) 230 V AC/20 A RST 20i3, coding black
Output LV halogen (female
12 V AC/20 – 70 W RST 20i2, coding signal
connector)
brown

Type
RST PSU 12/70 LVH

Circuit diagram
X1

3

max. 2 m cable length
Protection type
IP 65, 66, 67, 68 (3m; 2h), 69
Ambient temperature
0 °C up to +45 °C (derating from 35 °C)
Dimensions (length/width/height) 104/162/57.2 mm
Mounting option
4 elongated holes
Electrical connections
pluggable with RST 20i2...20i3

3Part No.
83.020.0904.0

X2

U

Accessories Covers
Suitable for all RST 20i2 and RST 20i3 codings

for malefor female

X3

Power supply unit 12 V for connecting halogen luminaires.
Connections not used have to be closed.

The covers have to be used to close all unused inputs and outputs. Without
these covers, only IP20 is achieved!

Type
Cover for male connector, captive against loss
Cover for male connector, not captive against loss
Cover for female connector, captive against loss
Cover for female connector, not captive against loss

Part No.
99.416.6205.2
05.564.4453.1
99.414.6205.2
Z5.564.4553.1

223

Compact / multidistribution units

2

Accessories

Radio switch / hand-held radio transmitter
Radio switch, 2/4 channels glossy withsuitable frame– glossy surface– batteryless and maintenance free
– for installation on flat surfaces with screws or adhesive pads (included in delivery)– the combination frames have to be ordered separately

TypeRadio switch, 2 channels

Radio switch, 4 channels

Colorpure whitepure whitepure white
aluminumaluminumaluminumMarking
I/0(▲▼)

pure whitepure whitepure white
Piano black
aluminumaluminumaluminum

I/0
(▲▼)

I/0
(▲▼)

I/0
I/0
(▲▼)

Part No.
F0.000.0025.0
F0.000.0025.2
F0.000.0025.4
F0.000.0026.8
F0.000.0027.0
F0.000.0027.2
F0.000.0025.1
F0.000.0025.3
F0.000.0025.5
F0.000.0026.0
F0.000.0026.9
F0.000.0027.1
F0.000.0027.3* 2 channels represent a rocker in neutral center position. This function is defined in the receiver.
* 4 channels represent two rockers in neutral center position. This function is defined in the receiver.

This push button series features a glossy, smooth surface. The
radio switches with 2 or 4 channels do not require batteries ormaintenance. The rockers are in neutral central position andwithout marking with 1/0 or up/down symbols. The matchingframes for these push buttons can be found below.

Frame for installation of the 2/4 channel glossy radio switches.
Suitable for vertical and horizontal mounting.

Handheld radio transmitter, 4 channels

Type
Combination frame 1-fold
Combination frame 2-fold
Combination frame 3-foldColorpure whitepure whitepure white

Combination frame 1-fold
Combination frame 3-foldpiano black
piano black

F0.000.0026.5
F0.000.0026.7

Combination frame 1-fold
Combination frame 2-fold
Combination frame 3-foldaluminumaluminumaluminumF0.000.0027.4
F0.000.0027.5
F0.000.0027.6

224Part No.
F0.000.0025.6
F0.000.0025.7
F0.000.0025.8

Handheld radio transmitter– Batteryless and maintenance-free– For stick-on surface mounting or as a handheld remote control.

Type
Handheld radio transmitter
Handheld radio transmitter
Handheld radio transmitter

Batteryless and maintenance-free 4-channel handheld
transmitter for direct control of the actuators.

MarkingColorpure white RAL 9010
black RAL 9005
silver coatedMarking

Part No.
F0.000.0009.1
F0.000.0009.2
F0.000.0009.3

Accessories

Radio switch / hand-held transmitter
Convenient hand-held transmitter
Radio channels
Configurable levels

51232

Displays
Texts and symbols
Lock
TimersSpeed dial keys
Dimensions (length/width/height)

Time, date, temperature
pre-defined or configurablewith pin code328
165/55/21 mm

TypeConvenient hand-held transmitter

Special EnOcean function:
Power supply:Supply with batteries
Charging device

Part No.
F0.000.0024.4

EnOcean service function, e.g. ID display, quality ofradio signals, and a radio link test (enables range test
between two hand-held terminals)
3 AAA-NiMH power packs(included in delivery)
USB charging device and separate
USB cable (included in delivery)

The convenient hand-held transmitter allows for control of the complete building. Whether
complex lighting concepts or comprehensive actions following a detailed schedule: This handheld terminal lets you program building functions in the twinkling of an eye. Menu navigation is
intuitive and is supported by easily understandable symbols.
Additionally, the device offers service functions for the installer regarding range planning andserves for function testing during commissioning.
Included in delivery• Batteryless and maintenance-free• for mounting on flat surfaces with screws or adhesive pads
(included in delivery)• The radio switches fit the frames with 55mm installation size of the vendors and theirdesigns listed:– Berker: S1, B1, B3, B7 Glas
– Gira: Standard 55, E2, Event, Esprit– Jung: A500, A plus
– Merten: M-Smart, M-Arc, M-Plan
TypeRadio switch, 2 channels

Color
white
anthracite
aluminum finish

Marking
I/0
I/0
I/0

Part No.
F0.000.0005.6
F0.000.0007.5
F0.000.0007.6

Radio switch, 2 channels

white
anthracite
aluminum finish

(▲▼)
(▲▼)
(▲▼)

F0.000.0005.8
F0.000.0007.7
F0.000.0007.8

Radio switch, 4 channels

white
anthracite
aluminum finish

I/0
I/0
I/0

F0.000.0005.7
F0.000.0007.9
F0.000.0008.0

Radio switch, 4 channels

white
anthracite
aluminum finish

(▲▼)
(▲▼)
(▲▼)

F0.000.0005.9
F0.000.0008.1
F0.000.0008.2

Batteryless and maintenance-free radio switches with 2/4 channels for direct control of theactuators. The rockers in neutral center position are marked with I/O or Up/Down( ▼) symbols. These 55x55 mm switches enable installation in various designs of various
manufacturer• Multivendor radio switches with 2/4 channels (light) (I / 0)
• the rockers are printed with I/0 symbols• Multivendor radio switches with 2/4 channels (sunblind) (Up / Down) (▲ ▼)• the rockers are printed with Up/Down (▲ ▼) symbols

225

Compact / multidistribution units

Multivendor radio switch, 2/4 channels

Distribution units

Compact and multiple distribution units
Flexibility according to RST® modularity

The pluggable distributors play a major role inpower or signal distribution. In their simplest
function, they merely have to provide branches in
the required locations. Practice shows, however,that the requirements may be much more complex.
Examples can be found in rotary A/C current
distributors and distributors with integrated finefuses, all the way through to boxes with integrated
electronics, such as constant current sources,
voltage sources, or radio actuators.

Two housing variations are the basis:
a flat design with up to four slots, and a highdesign with a total of up to eight slots. Alongsidea customized configuration with the new RST16i
device connectors, the existing components of
the RST20i and RST25i lines can also be used forvariety, of course.
The coded connectors give you the security of aclear distinction between different circuits – noneed to redo any incorrect connections. In addition
to the compact and multiple distributors, standard
distribution boxes can also be customequipped with
device connectors.

Example226

Distribution units

Special variant request –please complete and fax: +49-951-9326-996

X2

X1

No.

No.

No.

No.

Input, Ausgang
oder verschlossen
IN, OUT OR CLOSED

Ausgang oder verschlossen
OUT OR CLOSED

X5

X6

Ausgang oder verschlossen
OUT OR CLOSEDNo.

X8Ausgang oder verschlossen
OUT OR CLOSED

X7

No.

No.

Compact / multidistribution units

X3

X4
Ausgang oder verschlossen
OUT OR CLOSEDNo.

Ausgang oder verschlossen
OUT OR CLOSED

Bitte die benötigten Komponenten (Artikelnummer oder Polzal und Farbe) ergänzen und Verdrahtung einzeichnen.
Please add required components (either article code or number of poles and color) and the wiring scheme.

227

Technical data

RST ® compact and multi-distribution units

228

Technical data

Material:

Contact parts: brass, silver-plated
Housing parts: thermoplastic material PA 66, halogen-free, V2
Sealing material: NBR

Wiring:Individual wires 2.5 mm2, halogen-free(other cross-sections on request)

Regulations:

DIN VDE 0606 T200; DIN EN 61984 (VDE 0627); VDE 0110
IEC 60999

Approvals:

VDE
You can find the direct assignment of approvals and part numbers in the internetin the eShop under http://eshop.wieland-electric.com, or consult us.

Degree of protection:

IP66 / 68 (3m; 2h) / 69
Special variants may occur different degrees of protection.

IK code:

IK 07 (2 Joule) according to DIN EN 62262

Rated voltage:

250 V / 400 V

Rated current:

20 A (25 A)

Coding:Mechanical coding symbolized by color code.
Gray and black with the same mechanical coding.
Other codings are optional.

Note:

Protection against shock generally guaranteed even when disconnected.
Ground conductor leading. Connection to the live cable must be with a female connector
according to the regulations.
It is therefore not possible to have a ring circuit arrangement!
Only pluggable in the correct pole configuration; 1-pole cannot be connected.
Contacts protected against strain on the cable. All components can be interlocked.
A locking device is required for DIN EN 61535 approval.
DIN VDE 0606 T200 conformity does not automatically exclude the danger of confusion
with third-party installation plug connector systems!
Installation plug connector systems are no substitute for national plug/outlet systems
for domestic use.

Compact / multidistribution units

Operating temperature: -40° C up to +100° C

229