VeriSafe™ Access Control Kit

S P E C I F I C AT I O N S H E E Tapplications

Access Control Kit

The VeriSafe Access Control Kit provides an added layerof protection by preventing enclosure doors from being
opened until the absence of voltage is confirmed. TheAccess Control Kit provides an integrated solution thatcan be added to new or existing AVT installations.
When the AVT confirms the absence of voltage, a signal
is sent to disengage the lock. The system can be poweredby auxiliary power within the enclosure or via an optional
battery. The kit contains the components and hardware
necessary to incorporate this functionality into
electrical enclosures.
™

Access Control Kit containing
Enclosure Bracket, Latch Bracket,
Rotary Latch, Striker, Cam Latch,
Short Cam, andWire Harness:
VS-ACK-CPWR
Accessories
Extension Kit Containing
Extension Brackets
and Long Cam:
VS-ACK-EXT
Spare Key
for Cam Latch:

VS-ACK-KEY

Battery Kit Containing
Assembled Battery Casethat is DIN
Rail Mounted:
VS-ACK-BATTERY

components

Related Products

VeriSafe™ Absence of Voltage
Tester (not included)

VeriSafe™ AccessControl Kit

Access Control
Battery Kit

key features and benefits
Smart Technology:

Prevents enclosure from being access until absence ofvoltage is confirmed by AVT
Monitor latch status (optional)
Monitor door status (optional)

Enhanced Safety:

Protects personnel from electrical hazards
Latch automatically relocks upon closure
Remains locked if auxiliary power is lost

Ease of Installation:

Key hardware included for quick and easy installation
Flexible design for use with multiple enclosure types
Use existing 12-24Vdc power or optional battery

Robust Design:

Heavy-duty locking mechanism
Includes mechanical overrideCompatible with Type (NEMA, CSA, UL) 4 and12 enclosures

w w w . pa n d u it.c o m

VeriSafe™ Absenceof Voltage Tester with
2 ft. system cable,
3 ft. sensor leads: VS-AVT-C02-L03
VeriSafe™ Absenceof Voltage Tester with
8 ft. system cable,
10 ft. sensor leads: VS-AVT-C08-L10

VeriSafe™ Access Control Kit
technical information

ROTARYLATCH

ENCLOSURE
BRACKETSTRIKER

Latch Assembly Specifications• Rated NEMA/UL/CSA Type 4 and 12• Operating Temperature:-13°F to 140°F (-25°C to 60°C)• Power Input: 12-24 Vdc or Battery• Operating current: less than 500mA at 12Vdc
CAM
LATCH

LATCH
BRACKET• Push-to-close latch with electronic release

VeriSafe™ Access Control Kit• Heavy duty cast aluminum striker

Top View• Integrated latch and override mounting bracket• Includes keyed mechanical override
WIRE
HARNESS
PLUG• Outputs provide feedback on status of latchand door position (optional)• Panel lip range ½" - 5 ½" with ½" increments• Use on independent door handles only

MANUALOVERRIDE
LATCH

MECHANICALOVERRIDE

Maximum Lip Range

Battery Specifications (optional)

Back View
PANEL
MOUNT• Operating Temperature:-40°F - 140°F (-40°C - 60°C)• Mountable via DIN rail or side panel• Estimated capacity: 1 cycle per week for 10 years

DIN RAIL
MOUNT• ANSI-1604LC

VeriSafe™ Access Control Battery Kit

schematic12Latch Wiring Connections

Power Source
12-24 Vdc Poweror Battery

3

1Ground (-)

2Power (+)

3Control Signal from AVT

4

Latch Status (optional)

12

5

Not Used

34

Door Status (optional)

566

4Electronic Latch

A1 VeriSafe AVTModule
A2 Isolation
Output Contacts
B1 SIL 3 (IEC 61508)
B2™

Latch Status
Door Status

WORLDWIDE SUBSIDIARIES AND SALES OFFICESPANDUIT CANADA
Markham, Ontario
cs-cdn@panduit.com
Phone: 800.777.3300

PANDUIT EUROPE LTD.
London, UK
cs-emea@panduit.com
Phone: 44.20.8601.7200

PANDUIT SINGAPORE PTE. LTD.
Republic of Singapore
cs-ap@panduit.com
Phone: 65.6305.7575

PANDUIT JAPANTokyo, Japancs-japan@panduit.com
Phone: 81.3.6863.6000

PANDUIT LATIN AMERICA
Guadalajara, Mexico
cs-la@panduit.com
Phone: 52.33.3777.6000

PANDUIT AUSTRALIA PTY. LTD.
Victoria, Australia
cs-aus@panduit.com
Phone: 61.3.9794.9020

For a copy of Panduit product warranties, log on to www.panduit.com/warranty

For more information
Visit us at www.panduit.com
Contact Customer Service by email: cs@panduit.com
or by phone: 800.777.3300©2019 Panduit Corp.
ALL RIGHTS RESERVED.

SFSP12--SA-ENG
10/2019