Multicrest
fire alarm system

FIRU009-R-LCD

TMN3060

LCD-type Remote AnnunciatorFeatures• UL 864, 9th edition listed• 40 letters x 4 lines LCD unit
• 11 status LEDs
• 6 system control switches• Key lock switch to protect system control switch operation• Built in buzzer• Surface mounting or near flush mounting applicable• White or Red color enclosure• Three knockouts on the top, bottom and back of enclosure• Easy installation

Description
The FIRU009-R-LCD is a LCD remote annunciator for the Integlex Multicrest™ N3060 Fire Alarm Control Panel. The FIRU009-R-LCD
communicates, using a RS-485 connection, with the N3060 FACP and provides indications of Alarm, Supervisory, Trouble and other systemstatuses and system control functions.
The FIRU009-LCD is equipped with a 40 letters x 4 lines LCD display, 11 status LEDs, a built in buzzer, and 6 system control switches. The LCD
and the LEDs work together to visually inform the operation of the system status. The status LEDs are labeled as Power On, Alarm, General Alarm,Supervisory, Acknowledge, Pre-Discharge, Discharge, Signal Silence, Trouble, Battery Trouble, and Ground Fault. The buzzer audibly attracts theoperator’s attention during status change occurrence. The system control switches are only operable when a key lock switch is set to the enableposition. The functionality of these system control switches is equivalent to those of the N3060 FACP.
The RS-485 remote annunciator connection supports NFPA Class B (Style 4) wiring and the maximum length of 1.2 km (4000 ft). A maximum of
30 remote annunciators can be connected per N3060 FACP.
Each FIRU009-R-LCD shall have a remote annunciator number for its identification in a system. The remote annunciator number shall be set byrotary switches in FIRU009-R-LCD.
The FIRU009-R-LCD requires 24 VDC input power to operate. The 24 VDC input power can be provided from the N3060 FACP or a remote power
supply. The internal power supply of FIRU009-R-LCD converts the 24 VDC input power to 5 and 3.3 volts for use of the internal circuitry.

Operating information
Part No. PCA-N3060-LCDAN: LCD with membranePart No. ECL-N3060-LCDAN-NW or R: Enclosure for LCD-AN

Specifications
No.
1234567891011Item
Maximum 24 VDC current
Ambient operating temperature range
Maximum RA bus lengthMax. RA bus wiring resistanceMax. RA bus wiring capacitance
Applicable baud rates of RA-Bus
Annunciator buss wiring style
Maximum annunciator
Annunciator connection
Enclosure Rating
Dimensions

Specification
100 mA
0 to 49 °C (32 to 120 °F)
1.2 km (4000 ft)
40 Ω
0.4 µF
2400, 4800, and 9600 bps
NFPA Class B (Style 4)30 units
RS-485
NEMA – 1 (indoor use only)
149 mm (5.87”)(H) x 284 mm (11.19”)(W) x 57 mm (2.24”)(D)3-Ø28mm (1.10inches) Knockouts
270mm(10.63inches)

25mm (0.98inches)

Installation and Wiring Information

135mm (5.31inches)

149mm (5.87inches)
280mm (11.18inches)

50mm
50mm
(1.97inches) (1.97inches)

228.6mm(9inches)

1.6mm(0.06inches)

55mm(56.6mm)(2.17inches)(2.23inches)

To the next annunciator or LED Drive Module

TB1
24 VDC (+)+

24 VDC (-)

DC24V

-

RS485 ++

RS485 --RS485

Annunciator or LED Drive Module

TB4

Power Limited
Power Supply Board(PCA-N3060-PSU)
ANNUNCIATOR+-

AUX+

AUX-

NOTE
・The information contained herein does not purport to cover all the details or variations of the equipment described, nor to provide for every
possible contingency that may be met in connection with its installation, operation or maintenance.
・Specifications are subject to change without notice. Contact Nohmi before relying on the information.
・Actual performance is based on proper application of the product by a qualified professional.
・Should further information be required or should particular concerns arise that are not covered sufficiently for the purchaser’s purposes, thematter should be referred to Nohmi or your nearest distributor.

Contact• Head Office: 4-7-3 Kudan-Minami, Chiyoda-ku, Tokyo
102-8277, Japan• Phone: (81) 3 - 3265 - 0231
• F A X: (81) 3 - 3265 - 5348
URL http://www.nohmi.co.jp/english/

Catalog Number 131024Ⓓ-F-17800