Multicrest
fire alarm system

FRRJ001-Y-4F
FRRJ001-Y-16F
ADDRESSABLE MODULE FOR INITIATING DEVICES
4 -ADDRESS TYPE & 16-ADDRESS TYPETM

FRRJ001-Y-4FFeatures• 4 & 16 consecutive addresses per unit
• NFPA Class A (Styles 6 & 7) and Class B (Style 4) for SLC• NFPA Class B (Style B) for IDC• Electronic address setting• Slim unit
• Easy installation

FRRJ001-Y-16F

Description
The Addressable Module for Initiating Devices 4-address type and 16-address type are used to supervise the status of conventional initiating
devices connected on each initiating device circuit (IDC). 4 consecutive addresses can be configured to FRRJ001-Y-4F per unit, and 16
consecutive addresses can be configured to FRRJ001-Y-16F per unit. The FRRJ001-Y-4F and FRRJ001-Y-16F detect alarm conditions andreport to the Fire Alarm Control Panel (FACP). The IDC wiring style is applicable to the NFPA Class B (Style B). When the FRRJ001-Y-4F or theFRRJ001-Y-16F detects an alarm, the module is latched until the system is reset.
The FRRJ001-Y-4F and the FRRJ001-Y-16F are slim units, and they can be installed easily.

Ordering Information
Model no. FRRJ001-Y-4F
Model no. FRRJ001-Y-16F

Specifications
No.
123456789Item
Rated voltage of SLC input power (S+,S-)
Maximum current consumption of SLC (S+,S-)
Applicable SLC wiring style
Operating voltage of external power supply line (PF, PFC)
Rated output voltage of IDC (C, L)
Maximum module standby current of IDC 24VDC (C, L)
Maximum detector standby current of IDC 24VDC (C, L)
Maximum module and detector alarm current of IDC 24VDC (C, L)
Applicable IDC wiring style10

Number of address per unit

1112131415

Maximum wiring resistance of IDC (C, L)
Maximum wiring capacitance of IDC (C, L)
End-of-line device for IDC (C, L)
Operating temperature range
Operating relative humidity range

16Dimensions

Specification
24.0V
250µA
NFPA Style 4, 6, and 7
24.0V
24.0V
FRRJ001-Y-4F: 1.50mA , FRRJ001-Y-16F: 6.40mA
1.35mA30mA
NFPA Style B (i.e. Class B)
FRRJ001-Y-4F: 4 addresses
FRRJ001-Y-16F: 16 addresses
50Ω
1µF
Model no. FZE016A-10°C to 50°C (14°F to 122°F)
20 to 85% (non-condensing)
FRRJ001-Y-4F: 68mm (2.68 inches )(H)×232mm (9.13 inches)(W)×34mm (1.34 inches) (D)
FRRJ001-Y-16F: : 68mm (2.68 inches )(H)×232mm (9.13 inches)(W)×74mm (2.91 inches) (D)Setting the Address
Each addressable module, smoke detector, heat detector and combination detector must have the address set before connecting the device tothe Signaling Line Circuit (SLC) loop. The address is set using the hand-held device programmer or the addressing feature on the control panel.

Compatible Conventional Detectors
Series/Model Number
FDS01U
FDS226 series
FDS240 series
FDK01U
FDKL01U
FDK226 series
FDK229 series
FDK246 series
FDK228 series
PSD7155D

TypeIonization
Ditto
Ditto
Photoelectric
Photoelectric with fixed heat
Photoelectric
Ditto
Ditto
Ditto
Ditto (Product of Kidde-Fenwal)

Maximum connectable number
20 units
30 units
30 units
20 units
20 units
30 units
30 units
30 units
30 units
20 units

Installation
Figure 1: Installation in an electrical enclosure

Wiring Diagram
Figure 2: Wiring diagram of FRRJ001-Y-4F

To conventional
detectors
To conventional
detectors
To conventional
detectorsTo conventional
detectors

24VDC (-)

L4C4L3

From FACP orprevious module

24VDC (-)

L2

L1

Signal line (-)
Signal line (+)

C3C224VDC (+)

To FACP or nextmodule

24VDC (+)
Signal line (-)
Signal line (+)

C1PF
PFC
SS+
PF
PFC
SS+

*Note: In the case of FRRJ001-Y-16F, the terminals for C and L are available up to the no 16.

NOTE・The information contained herein does not purport to cover all the details or variations of the equipment described, nor to provide for every
possible contingency that may be met in connection with its installation, operation or maintenance.
・Specifications are subject to change without notice. Contact Nohmi before relying on the information.
・Actual performance is based on proper application of the product by a qualified professional.
・Should further information be required or should particular concerns arise that are not covered sufficiently for the purchaser’s purposes, thematter should be referred to Nohmi or your nearest distributor.

Contact• Head Office: 4-7-3 Kudan-Minami, Chiyoda-ku, Tokyo
102-8277, Japan• Phone: (81) 3 - 3265 - 0231
• F A X: (81) 3 - 3265 - 5348
URL http://www.nohmi.co.jp/english/

Catalog Number 151001Ⓓ-F-19800MS01