Package Type Foam
Fire Extinguishing SystemⅢ
Low to Medium Expansion Foam Fire Extinguishing System

Suitable to prevent fires of production
machinery incidents and flammableliquids in production facilities

A high-performance and easy-to-use,
self-contained foam fire extinguishing system■ Eﬀective and fast-acting

The medium-expansion foam with powerful extinguishing
agents and the low-expansion foam with longer discharge
range can be switched easily by hand for optimum
performance and eﬃcacy.

■ Easy to use for a single person

The lightweight rubber hose with internal windingmechanism allows a single person to pull the hose in any
direction easily.

■ No need for plumbing or electrical works

The package type MIDEXⅢ does not require plumbing, electrical
works, water supply, or external pumps.
The compact and lightweight cabinet can be placed exactly whereneeded, and its double doors allow easy access with minimalclearance.

Easy maswitch nualing

Ⅲ
Low to Medium Expansion Foam Fire Extinguishing System■ Condition during ﬁreﬁghting

Dischargeable more than 3,000 liters of medium-expansion foam.

■ Condition after ﬁre extinguishedThe foam residue has slight impact on surrounding environment
and is easy to clean up.

Fires of industrial machinery and equipment are best treated with medium-expansion foam of the MIDEXⅢ, which is able to reachinaccessible areas such as behind screens or at the rear of the machine by ﬂowing over the top and down the sides.
Note: Foam works only on areas where it can reach.

■ Suitable applications
Anywhere that flammable liquids or materials are used.
【Examples】●Metalworking and machining equipment, cutters, hydraulic equipment such as presses, oil cellars, painting equipment●Oil feed systems ●Various testing equipment ●Vehicle maintenance workshops ●Printing facilities●Small-scale hazardous material storage facilities ●Small-scale rubbish pits

■ Speciﬁcations■ Dimensions (mm)Product code
0700

1,400

25

MRFJ001

Operating environment
Drive system
Working pressure(pressure regulator setting)Operating temperature range
Enclosure material
Dimensions
WeightColorClassiﬁcation
Extinguishing
Foam typeagent
Tank capacity
Gas type
Pressurized
No. of cylinder
gas cylinder
Capacity
Winding mechanism
HoseLength
Foam switcherDischarge time
NozzleDischarge distance (approx.)
Expansion ratio
Applicable ﬁre classiﬁcations

IndoorManual
0.94 MPa0°C ‒ 40°CSECC
700 mm (W) x 250 mm (D) x 1,400 mm (H)Approx. 130 kg
Ivory (JPMA code E22-90D)
Aqueous foamed ﬁre extinguishing agent
Aqueous ﬁlm forming foam
53 L (26.5 L x 2 tanks)
NitrogenOne
3.4 L (3.0 L for India market)
Internal winder
20 m
Toggles between low and medium expansion foam
At least 70 seconds (at 20°C)
10 m for low-expansion foam (at 20°C)
5 m for medium-expansion foam (at 20°C)
Low-expansion: at least 5 times (at 20°C)
Medium expansion: at least 60 times (at 20°C)
Class A and B

Note: Please inquire for details regarding use on certain hazardous materials that contain aqueous solution.
●In internal testing, the MIDEXⅢ successfully extinguished a 4 m2 pan ﬁre of n-Heptane (similar component to gasoline) within 40 seconds.
●Product performance also rated by the Hazardous Materials Safety Techniques Association (KHK) in Japan.
Permitted for use as Type 3 fire-fighting equipment in hazardous goods facilities by application only.
(for Buildings and Other Structures and Type 4 Hazardous Materials)

NOTE: ● The information contained herein does not purport to cover all the details or variations of the equipment described, nor to provide for every possible

contingency that may be met in connection with its installation, operation, or maintenance.
● Specifications are subject to change without notice. Contact NOHMI before relying on the information.
● Actual performance is based on proper application of the product by a qualified professional.
● Should further information be required or should particular concerns arise that are not covered sufficiently for the purchaser’s purposes, the mattershould be referred to NOHMI or your nearest distributor.

●HEAD OFFICE： 7-3, Kudan Minami 4-chome,

Chiyoda-ku, Tokyo 102-8277, Japan●PHONE：（81）
3-3265-0231●F A X：（81）
3-3265-5348●U R L： https://www.nohmi.co.jp/english/

181015 D -E-7500YO1