Multicrest
fire alarm system

TMCNI016N

System Monitoring Program (SMP)
Features• Max. 195,840 addresses configurable per SMP• Max. 64 nodes available on network• Remote monitoring of networked systems via VPN• Max. 1,000,000 symbols available per SMP• DXF & BMP data applicable to floor plans• Group functionality same as FACP
• Current event list
• Event log for up to 50,000 events per SMP• Analog value trend indication• Sensor monitoring• 4 system control switches• Designed for Microsoft Windows XP, Vista, 7, 8 and 10Description
The SMP is software to be installed in a personal computer. By connecting to the FACP network via the System Interface Unit (SIU), the SMP provides the systemwith an ability to monitor the FACPs on the network, displays events currently occurring, and controls systems.
The SMP consists of three modes such as the Design Mode, Run Mode, and Remote Mode. In the Design Mode, registered device symbols are arranged on floor
plans that come from DXF or BMP formatted data files, and the arranged symbols are given their addresses that are corresponded to addresses in FACPs. The
SMP can utilize the configuration data of FACP to prepare the symbols of addressable devices. By reading the configuration data of FACP into itself, the SMP
automatically creates a list of device symbols that should be configured on the floor plans. A node number and a group number are assigned for each SMP for its
identification on the network.
In the Run Mode, when any event occurs in the group to which the SMP belongs, the corresponded device symbols arranged in the Design Mode start flashingfor notification to the operator. The device symbols are white under the normal monitoring condition. The symbols are changed to magenta for the pre-alarm
condition, orange for the supervisory condition, yellow for the trouble condition, and red for the alarm condition. Details of currently occurring events are also
displayed on the screen. The details consist of event occurrence date/time, device classification, status, device message, address number, and zone number.
The SMP is capable of monitoring FACPs at a location remote from the FACPs. This functionality is available in the Remote Mode via VPN utilizing a network device.
A maximum of 64 FACPs can be monitored by a remote SMP.
The SMP is equipped with four system control switches the same as FACPs’, such as Acknowledge, Signal Silence, Fire Drill, and System Reset. These switches
are enabled only in the Run Mode. Their operations are effective in the group to which the SMP belongs.
The Integlex Multicrest N3060 is applicable to Design Mode, Run Mode, and Remote Mode. The Integlex Multicrest 508 is applicable to Design Mode and RemoteMode only.

Other functions in Run Mode• Event log: An SMP is able to store up to 50,000 events in its event log. The event log data can be saved as a file.
• Trend data display: Trend data of pre-registered analog detectors can be displayed in graph format.
• Sensor monitoring: Analog detectors’ current values (smoke density or temperature) can be displayed.
• Zoom: Floor plans can be zoomed by mouse wheel.
• Protection: A dedicated key protection is required for SMP operation.
• Sound: Either wave or beep is selectable.
• Maintenance report: Analog detectors current statuses can be displayed.
• Print: Various information can be printed.

SMP Specifications
No.

Item1Resolution234567

Max. configurable address no. per SMP
Max. configurable screen no. per SMP
Max. register-able symbol no. per SMP
Max. configurable symbol no. per screen
Event log capacity
Max. number of nodes on network

Required PC specifications
Specification
1024 x 768
1280 x 1024
1920 x 1080
1920 x 1200
195,840 addresses
1,000 screens
193 symbols
1,000 symbols
50,000 events
64 nodes

No.

Item

1

PC hardware

2

Operating system

3

Graphic

Specification
・Processor class: 200MHz or greater
・HDD space: More than 2 GB・Memory: More than 128MB
・Media format: DVD-ROM・Audio device: Sound card
・Port: COM port and USB port
・Audio output: SpeakerMicrosoft Windows XP, Vista, 7, 8 and 10
XGA:1024 x 768, high color (16bit)
SXGA:1280 x 1024, high color (16bit)
Full HD:1920 x 1080, high color (16bit)
WUXGA:1920 x 1200, high color (16bit)

Ordering information
Part No. CNI016N

Screen information

Top screen

Floor plan under alarm condition

Event log screen

System configuration

Serial / Ethermet
VPN Router
Converter

Serial / Ethermet
VPN Router
Converter

FACP
FACP

Local Area 1

NohmiNET
FACP

FACP

VPN Router

VPN Router

SIU

SMP（Run Mode）

Local Area 1

Serial / Ethermet
VPN Router
Converter

WAN

WAN
FACP

Serial / Ethermet
VPN Router
Converter

Local Area 2

SMP（Remote Mode）
FACP

SMP
(Remote Mode)

Remote Location

Remote Location

NohmiNET
FACP

Serial / Ethermet
VPN Router
Converter

FACP
SIU
FACP

SMP
（Run Mode）

Local Area 3

Local Area 2

SMP of Integlex Multicrest N3060

SMP of Integlex Multicrest S508

NOTE・The information contained herein does not purport to cover all the details or variations of the equipment described, nor to provide for every
possible contingency that may be met in connection with its installation, operation or maintenance.
・Specifications are subject to change without notice. Contact Nohmi before relying on the information.
・Actual performance is based on proper application of the product by a qualified professional.
・Should further information be required or should particular concerns arise that are not covered sufficiently for the purchaser’s purposes, thematter should be referred to Nohmi or your nearest distributor.

Contact• Head Office: 4-7-3 Kudan-Minami, Chiyoda-ku, Tokyo
102-8277, Japan• Phone: (81) 3 - 3265 - 0231
• F A X: (81) 3 - 3265 - 5348
URL https://www.nohmi.co.jp/english/

Catalog Number 180820Ⓓ-F-18603