Product Catalog“Nohmi Quality” you can trustWe give shape to the“FUTURE OF FIRE SAFETY”
From the viewpoint of social safety and industrial risk management, there is an increasing demand for
improvements in the quality of fire prevention.
Although it is obvious that safety is as important as air, people are only now re-evaluating safety andappreciating its importance.
It is already difficult to ensure safety even when a building is viewed from the simple container concept.
People now have diverse lifestyles so fire protection systems peculiar to the building must be constructed.
As a result, we must understand both how buildings are used and the lifestyles of the occupants.
At the same time, unique, sophisticated fire protection technology is required to also take into account theconstruction and function of buildings as well as innovations in external cladding and internal finishingmaterials.
Take a look at our fire alarm systems. Nohmi’s state-of -the-art technology features ingenious design
combined with features that make our customers lives safer and more comfortable.
Nohmi's worldwide corporate brand identity, NOHMI, is based on this concept of providing
each customer with the most suitable fire protection system for their needs
by making the most of our advanced know-how gained over many years.

Addressable fire alarm systems

contents

1. Addressable fire alarm control panels and annunciators

P3

2. Analog addressable fire detectors
3. Addressable detector bases

P4

4. Addressable modules

P5

5. System monitoring program
6. Address setting unit

P8

Conventional fire alarm systems
1. Conventional fire alarm control panels and annunciators

P9

2. Conventional fire detectors

P10

Flame detectors and control panels

P11

Flame detectors
Aspirating smoke detection system
Conventional aspirating smoke detector

P12

1. Notification appliances

P13

2. Manual stations
3. Location lamps
4. Remote indicator lamps

P13-14

5. Combination boxes

P14

6. Explosion proof devices

P14

7. Fire door closing devices

P15

8. Lightning arrester units

P15

9. Flame monitoring system

P15

10. Miscellaneous

P16

OthersFoam fire extinguishing systems
Low to medium expansion foam fire extinguishing system

P17

Nitrogen gas fire suppression systems
1. Clean agent fire suppression systems & Components

P18

2. Fire suppression system for object protection

P18

Addressable fire alarm systems
1. Addressable fire alarm control panels and annunciators
BrochureFire alarm control panels[1] N3060- 1 to 12 loops per FACP
- 127 or 255 addresses per loop selectable- Max. 3,060 addresses per FACP
- 10.4 inch color touch screen- MAX. 64 nodes per network- NFPA Class A, B, and X (Style 4, 6, and 7)
for SLC- 4 NACs, 6.0A in total (optionally expandable up
to 16A with an additional power supply unit)- 4,000 events history buffer- 110 to 240V, 50/60Hz for AC universal input- 12Ah to 65Ah back up battery
capacity- UL listed
Data Sheets & Video[2] N765- 1 or 3 loops per FACP
- 127 or 255 addresses per loop selectable- Max. 765 addresses per FACP
- 160 characters LCD (40 letters x 4 lines)- MAX. 64 nodes per network- NFPA Class A, B, and X (Style 4, 6, and 7)
for SLC- 2 NACs, 5.0A in total- 4,000 events history buffer- 100 to 240V, 50/60Hz for AC
universal input- 7Ah to 40Ah back up battery
capacity- UL listed

Data Sheet

Annunciators[1] LCD-type remote annunciator, FIRU009-R-LCD- 40 letters x 4 lines LCD- 11 status LEDs
- Key lock switch to protect system control
switch operation- 6 system control switches

Data Sheet- Built-in buzzer- 24VDC for rated operating voltage- UL listed[2] LED-type remote annunciator, FIRU009-R-LED- 16 zones status indicators- 6 system status LEDs
- Key lock switch to protect system control
switch operation- Built-in buzzer- 24VDC for rated operating voltage- UL listed[3] LED driver module for mimic panel, PCA-N3060-LDM- 32 LED driver outputs for zone statusindications- C onsecutive or random zone number
assignment available- Audible alarm device (Built-in buzzer)

3- P ower supply status LED and signaltransmission status LED- 24VDC for rated operating voltage- UL listed

2. Analog addressable fire detectors
Analog photoelectric smoke detector, FDKU033-D & FDKU033-D-X- Very low profile (28.7mm/1.13 inch only inheight)- Wide alarm set-point range 5.1 to 11.0 %/m(1.57 to 3.50 %/foot)- True analog detector- UL listed smoke calibration and sensitivity- IP42

Data Sheets- Simple and accurate address setting
without mechanical switches- LEDs for 360° viewing- 22.0 to 24.0V for working voltage range of
SLC- UL listed (UL268 7th Edition)

Analog fixed temperature heat detector, FDLU019-D-X- Very low profile (30.7mm/1.21 inch only inheight)- 57℃ to 85℃ (135℉ to 185℉) heat sensor- True analog detector- Ambient temperature listing of 0℃ to 66℃(32℉ to 150℉)- Simple and accurate address setting
without mechanical switches- LEDs for 360° viewing- 22.0 to 24.0V for working voltage range of
SLC- UL listed

Analog rate-of-rise/fixed-temp. combination heat detector, FDHU003-D-X- Very low profile (30.7mm/1.21 inch only inheight)- 57℃ to 79℃ (135℉ to 174℉) heat sensor- True analog detector for fixed temperature- Rate-of-rise feature- Rate-of-rise operates when the temperature
increases 7℃ to 8℃ (12℉ to 15℉) per
minute occurs- Simple and accurate address setting
without mechanical switches- LEDs for 360° viewing- 22.0 to 24.0V for working voltage range of
SLC- UL listed

Analog photoelectric projected beam smoke detector, FDGJ002-D-X- Wide and high coverage within 100m
distance- Sensitivity drift compensation forcontamination or a slight shift in the
optical system- Light synchronized system to prevent false
alarms- Simple optical axis setting- Simple and accurate address setting
without mechanical switches- 24VDC for rated operating voltage of SLC

3. Addressable detector bases
2-terminal base, FZBU013-2Z

Data Sheets- Standard 2-wire detector base
- UL listed (UL268 7th Edition)44-terminal base, FZBU013-4Z- Standard 2-wire system with remote indication circuit- UL listed (UL268 7th Edition)

Isolator base, FZBU005-AIB- Short circuit isolator integrated in detectorbase- Self-restoring- Optional locking tab to prevent unwanted
removal- 22.0 to 24.0V for working voltage range of
SLC- UL listed (UL268 7th Edition)

Sounder base, FZBU005-ASB- Integrated sounder in detector base
- Sound output at 75 dB (UL 464 listed)- Sounder independent of detector- May be mapped to any device connectedto the control panel- Simple and accurate address setting
without mechanical switches- Optional locking tab to prevent unwanted
removal- 22.0 to 24.0V for working voltage range of SLC- UL listed (UL268 7th Edition)

4. Addressable modules
UL listed addressable modules

Data Sheets[1] Twin relay module, FRRU004-TRM4- Dry contact addressable module- Two typical form C dry contacts at 24VDC
2A, 125VAC 0.5A
- One simple LED for status indication- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed[2] Miniature contact module, FRRU004-MCM- Input signal addressable module, mini-size- NFPA Class B (Style B) for IDC- 5.1kΩ, 1/2W end-of-line resistor for IDC- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed[3] Single contact module, FRRU004-SCM4- Input signal addressable module- One simple LED for status indication- NFPA Class B (Style B) for IDC- 5.1kΩ, 1/2W end-of-line resistor for IDC

5- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed

[4] Dual contact module, FRRU004-DCM4- Input signal addressable module, two inputs- One simple LED for status indication- NFPA Class A (Style D) and Class B (StyleB) for IDC- One address in Class A, two addresses inClass B for IDC- 5.1kΩ, 1/2W end-of-line resistor for IDC in
Class B
- 22.0 to 24.0V for working voltage range of SLC- Simple and accurate address setting
without mechanical switches- UL listed[5] Conventional initiating zone module, FRRU004-CIZM4- Addressable module for conventional
detectors- One simple LED for status indication- NFPA Class A (Style D) and Class B (StyleB) for IDC- 15.7 to 22.6V output voltage range of IDC- 5.1kΩ, 1/2W end-of-line resistor for IDC in
Class B
- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed[6] Monitored output module, FRRU004-MOM4- Wet output addressable module- One simple LED for status indication- NFPA Class B (Style Y) for NAC- UL listed with potter/Amesco®, GENTEX®,
and Cooper Wheelock ® syncro-modules
and devices- 24VDC, 2A rating for connected device
power (releasing device and NAC)

- 5.1kΩ, 1/2W end-of-line resistor value for
notification appliance- 5.1kΩ, 1/2W with diode, end-of-line
device for releasing device- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed[7] Short circuit isolator, FQIU004-SCI- One simple LED for status indication- Self-restoring LED indication- 22.0 to 24.0V for working voltage range of SLC- UL listed[8] Analog input module, FRRU004-AIM- One simple LED for status indication- Monitors the analog input of 4 to 20mA
- 0.5A rating for connected device- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed[9] Gas suppression control unit, FRRU004-GSCU- Field control unit for gas suppression
systems- Two addresses- P ro g r a m m a b l e N A C , D I ( d i s c h a r g e
Indicator), abort, and manual releasecircuits- NFPA Class B (Style B) for IDC and Class B(Style Y) for NACs and DI- 2 NACs and 1 DI, 3.0A in total- 5.1kΩ, 1/2W end-of-line resistor for IDC
and NACs and DI- Equipped with changeover switch (Auto &Manual or Manual only) and countdown timer- Status LEDs for power input, changeoverswitch, abort, manual release, trouble,
suppression disabled, pre-discharge,
discharge- 22.0 to 24.0V for working voltage range of
SLC- Simple and accurate address setting
without mechanical switches- UL listed

6

Japan Standard Addressable Modules[1] Wet output module 4-circuit, 1 address, FRRJ001A-Y-S- 1 address with 4 circuits- Retur n signal per circuit for device
activation confirmation- Circuits applicable to input signals- 2A maximum voltage output per circuit- Dry typical form A contact for return signal- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

[2] Wet output module 16-circuit, 4 address, FRRJ001-Y-4S- 4 addresses with 16 circuits- Retur n signal per circuit for device
activation confirmation- Circuits applicable to input signals- 2A maximum voltage output per circuit- Dry typical form A contact for return signal- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

[3] Dry contact module 4-circuit, 1 address, FRRJ001A-Y-SS- 1 address with 4 dry contacts and 4 inputs- Return signals or input signals available- Dry typical form A contact at 30VDC, 2A
railing- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

[4] Dry contact module 8-circuit, 2 address, FRRJ001-Y-2SS- 2 addresses with 8 dry contacts and 8
inputs- Return signals or input signals available- Dry typical form A contact at 30VDC, 2A
railing- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

[5] Dry contact module 16-circuit, 4 address, FRRJ001-Y-4SD- 4 addresses with 16 dry contacts- Dry typical form A contact at 30VDC, 2A
railing- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

[6] Addressable module for initiating device 4 address, FRRJ001-Y-4F- 4 consecutive addresses per unit
- NFPA Class B (Style B) for IDC- N o h m i c o n v e n t i o n a l f i re d e t e c t o r scompatible- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

[7] Addressable module for initiating device 16 address, FRRJ001-Y-16F- 16 consecutive addresses per unit
- NFPA Class B (Style B) for IDC- N o h m i c o n v e n t i o n a l f i re d e t e c t o r scompatible

7- 24.0V for rated operating voltage of SLC- Simple and accurate address setting
without mechanical switches- Slim unit

5. System monitoring program
Data Sheets

System monitoring program, CNI016N- Max. 195,840 addresses configurable per
SMP- Max. 64 nodes available on network- Remote monitoring of networked system
via VPN- Max. 1,000,000 symbols available per SMP- DXF & BMP data applicable to floor plans- Group functionality same as FACP
- Current event list
- Event log for up to 50,000 events per SMP- Analog value trend indication- Sensor monitoring- 4 system control switches- Designed for Microsoft Windows 8 and 10

System interface unit, CSC004- NFPA Styles 4 and 7 wiring applicable- Max. 64 nodes available on network- Max. length between two nodes as600m for copper/metal cable, 2,000m
for 50/125 fiber optic cable, 1,700m for
62.5/125 fiber optic cable, and 5,000m
for 9/125 fiber optic cable- Status LEDs
- 110V and 240V for AC universal input

6. Address setting unit
FZAW004-P- Electric address setting compatible with all Nohmi
addressable devices

8Conventional fire alarm systems
1. Conventional fire alarm control panels andannunciators
Data Sheets

Fire alarm control panels[1] 5 zones without telephone system, FAPN202-R-5L- Dedicated 5 zones fire alarm system- Simple fire alarm functionality- Various test functions- Self-diagnosis system- Mis-operation inhibit function- Built-in surge arrestor for power lines- Back-up power supply (Ni-Cd battery)- 220V, 50/60Hz for AC input[2] 10 and 20 zones with telephone system, FAPN105N series- 10 and 20 zones fire alarm system
available- Various test functions- Self-diagnosis system- Mis-operation inhibit function- Built-in surge arrestor for power lines- Built-in telephone system- Fire zone indication by both zone plates
and digital display- 1,000 event log- Functions programmable at site
- Back-up power supply (Ni-Cd battery)- 220V, 50/60Hz for AC input[3] 30 to 100 zones with telephone system, FAPN104N series- 3 0 t o 1 0 0 z o n e s f i re a l a r m s y s t e mavailable- Various test functions- Self-diagnosis system- Mis-operation inhibit function- Built-in surge arrestor for power lines- Built-in telephone system- Fire zone indication by both zone plates
and digital display- 25 programmable dry contacts- 10,000 event log- Functions programmable at site
- Back-up power supply (Ni-Cd battery)- 220V, 50/60Hz for AC input

Annunciators[1] 5 zones without telephone system, FIPN203-S-5L- Dedicated to 5 or less 5 zones fire alarm system- Zone plate indication with red LEDs
- Audible device (electronic buzzer) equipped[2] 10 to 100 zones with telephone system, FIPN103 series- 10 to 100 zones fire alarm system applicable- Zone plate indication with red LEDs
- Built-in telephone system- Audible device (electronic buzzer) equipped92. Conventional fire detectors
Conventional spot type smoke detectors

Data Sheets[1] FDK series – FDK246N, FDK246, FDK246-X- Very low profile- 2-wire system- 24VDC for rated operating voltage- Small monitoring current of 45μA
- Remote indication circuit available (FDK246-X)[2] FDKU634-D-X- Very low profile (28.7mm/1.13 inch only inheight)- 2-wire system- Wide range input voltage 15.0 to 28.8VDC- High air velocity rating- LEDs for 360° Viewing- Sensitivity check by flashing LED- IP42- Remote indication circuit available- UL listed (UL268 7th Edition)

Conventional projected beam smoke detector,
FDGJ series – FDGJ103-D-X & FDGJ203-D-X- Wide and high coverage within 100m
distance- Sensitivity drift compensation ofcontamination or a slight shift in the
optical system- Light synchronized system preventing
false alarms- Simple optical axis setting- Optical remote test switch for easy
maintenance- 24VDC for rated operating voltage

Conventional rate-of-rise heat detector,
FDPJ series – FDPJ106-D, FDPJ206-D, FDPJ206-D-T, FDPJ206-D-M, FDPJ206-D-X etc.
- Low profile- 2-wire system- Rate-of-rise operates when thetemperature increases 10℃ (FDPJ106),
15℃ (FDPJ206 series) per minute occurs- Remote testing mechanism available(FDPJ206-D-T)- Response lamp holding circuit available(FDPJ206-D-M)- R e m o t e i n d i c a t i o n c i rc u i t a v a i l a b l e(FDPJ206-D-X)- 30VDC 75mA for contact ratings

Conventional fixed temperature heat detector,
FDLJ series – FDLJ906-D-65, FDLJ906-DW-65, FDLJ106-DW-X75, FDLJ106-DW-S75 etc.
- 65℃ or 75℃ operating temperature- 2-wire system- Physical protector equipped- Alarm response lamp (LED)- Water proof type available (FDLJ906DW-65, FDLJ106-DW-X75, FDLJ106DW-S75)- R e m o t e i n d i c a t i o n c i rc u i t a v a i l a b l e(FDLJ106-DW-X75)- Dry contact circuit available (FDLJ106DW-S75)- 30VDC 75mA for contact ratings (62mA
for FDLJ106-DW-S75)

10

Flame detectors
Flame detectors and control panels
Data Sheets

Non-explosion proof type flame detector[1] IR3 flame detector, PDCJ001-D- Infrared three-wavelength flame detector(with testing function)- Non explosion proof type
- 24VDC for rated operating voltage- Dustproof and waterproof (equivalent to“IP66”)- Horizontal and vertical 90° angle viewfor detection (the angle at which themonitoring distance is 1/2 to the front
direction)- Equipped with self-diagnosis function- High sensitivity (33cm 2 normal heptane
flame detector at 60m front distance)- Reliable fire detection CO2 resonanceradiation principle, operation on flickeringflame- Approximately 3 seconds for delay time(changeable by setting)[2] Addressable IR3 flame detector, FDCJ004-D- Infrared three-wavelength spot type flame
detector (with testing function)- Non explosion proof type
- 24VDC for rated operating voltage- Dustproof and waterproof (equivalent to“IP66”)- Equipped with self-diagnosis function- High sensitivity- Reliable fire detection CO2 resonanceradiation principle, operation on flickeringflame- Long monitoring range Max. 25m (50°from the center) to max. 45m (0° from thecenter)- Wide viewing area 100° (50° in all directions
from the center line of the detector
downward to the floor)- The Japanese standard approved product[3] Conventional flame detector, FDCJ002-D-X- Infrared type flame detector- CO2 resonance radiation principle,
operation on flickering flame- 2-wire system- 13 to 20m monitoring distance- 100° angle view for detection- With remote indication circuit- 24VDC for rated operating voltage- The Japanese standard approved product

Explosion proof type IR3 flame detector, PDCJ002-E- Infrared three-wavelength flame detector(with testing function)- Explosion proof type Exde II CT5 (Body:
Explosion proof type, Terminal: Increased
safety)- 24VDC for rated operating voltage- Dustproof and waterproof (equivalent to“IP66”)- Horizontal and vertical 90° angle viewfor detection (the angle at which themonitoring distance is 1/2 to the front
direction)

11- Equipped with self-diagnosis function- High sensitivity (33cm 2 normal heptane
flame detector at 60m front distance)- Reliable fire detection
CO2 resonance radiation principle,
operation on flickering flame- Approximately 3 seconds for delay time(changeable by setting)Dedicated control panel for flame detector[1] PAPJ002-R-4/8/12L(-P) for PDCJ001-D- 4, 8, and 12 zones or 75℃ operating
temper- 2-wire system- Physical protector equipped- Alarm response lamp (LED)- Water proof type available (FDLJ906DW-65, FDLJ106-DW-X75, FDLJ106DW-S75)- R e m o t e i n d i c a t i o n c i rc u i t a v a i l a b l e(FDLJ106-DW-X75)- Dry contact circuit available (FDLJ106DW-S75)- 100V±10%, 50/60Hz for AC input- 30VDC 75mA for contact ratings(62mA for FDLJ106-DW-S75)- Japanese notation[2] FPI012B-1L~5L-A, -D for PDCJ002-E- 1 to 5 zones (IR3 flame detector 1 unit /zone)- Wall mounting, Indoor type

- (FPI012B-1L~5L-A)
100V±10%, 50/60Hz for AC input(FPI012B-1L~5L-D)
24V±10% for DC input- Japanese notation

Aspirating smoke detection system
Conventional aspirating smoke detector
Protecview FDNA002-R- Super-high to low level sensitivity from0.001 to 20.0%/m- Total scattered light detection principle- Large flow rate fan- Bar graph smoke density indicator

Data Sheet & Video- Contact output (alarm, trouble)- Smoke density analog output (4-20mA)- 24VDC or 100 VAC for rated input voltage- Stand-alone system product12

Others
1. Notification appliances
Fire alarm bells – FBM01U-D, FBM023, FBM023-D, FBW013-EA- Motor driven type alarm bell
- High sound output with low current
consumption- Low RFI noise- Lead wire connection- 24VDC for rated operating voltage

Data Sheets- Indoor, Outdoor type (FBM01U-D)- Rainproof type available (FBW013-EA)- Polarized type available (FBM01U-D,
FBM023-D)- UL listed product available (FBM01U-D)

Strobe/Horn, NEC3-24WR- Low profile- Field selectable candela options of 15, 30, 60, 75, and 110- NAC synchronization feature with Nohmi Addressable FACPs or dedicated modules- 24VDC for rated operating voltage- UL listed

Strobe Light, S-24WR- Low profile- Field selectable candela options of 15, 30, 60, 75, and 110- NAC synchronization feature with Nohmi Addressable FACPs or dedicated modules- Instant voltage verification feature- 24VDC for rated operating voltage- UL listedHorn, EH-24R- Low profile- NAC synchronization feature with Nohmi Addressable FACPs or dedicated modules- Instant voltage verification feature- 24VDC for rated operating voltage- UL listed

2. Manual stations
Data Sheets

Manual Push Button, FMMN, FMRN, FMBN series –FMMN102-U, FMMN102-UW, FMMN202-U, FMRN102-U, FMBN102-U, FMBN102-UW- Cutting-edge compact design- Push-button-type- Easy reset after operation- Addressable and conventional types
available- 30VDC 500mA (FMMN & FMRN) for
contact ratings

13- Indoor and Outdoor types available- Telecommunication means provided(except for FMMN202-U)- Response lamp provided (except for
FMMN202-U)

Pull Station, FMM01U series - FMM01U-SK2, FMM01U-SK1- Single or dual action pull down activation- Key reset- 30VDC 1A or 125VAC 1A for switch
contact ratings- Terminal connectors- Gold plated SPST and contacts- High-gloss enamel finish- Plastic break rod- UL listed

3. Location lamps
FLPJ series – FLPJ002, FDPJ002-W, FLPJ004, FLPJ004-W

Data Sheets- Cutting-edge new design (FLPJ004, FLPJ004-W)- Noticeable red color- Low current and high durability- Wide and high visibility- Outdoor type available

4. Remote indicator lamps
FLL series – FLL061A-B, FLL061-C- White cover plate and red LED with translucence lamp cover- Two sizes available (70mm x 115mm and 65mm x 88mm)- 50mA maximum rated current

5. Combination boxes
Data Sheets

FWLN series- Three-in-one composition (location lamp,
manual push button, alarm bell)- Cutting-edge new design- Addressable and conventional available- Surface and recess mountings available- Easy installation and maintenance- Indoor / Outdoor type available

6. Explosion proof devices
Manual station, FMEJ202-RG- Flame proof and explosion proof product- Exde ll CT6 for explosion class and ignition
grade- Location lamp equipped- Applicable to both indoor and outdoor
uses- 24VDC for rated operating voltage

14

Fire alarm bell, EMB-6 DC24V- Rain proof and explosion
proof product- Exd ll BT4 for explosion classand ignition grade- 24VDC for rated operating
voltage

Location lamp, EC2B-110- Exde Ⅱ CT6 for explosion class andignition grade- 24V AC/DC rated operating voltage

7. Fire door closing devices
SLDJ004 series – SLDJ004-U-E, SLDJ004-U-M- Latch type
- Electrical resetting type and manual resetting type available- 24VDC for rated operating voltage

8. Lightning arrester unitsFZL116 series – FZL116-E-40L-T (40 terminals), FZL116-K1-80L-T (80terminals), FZL116-K1-120L-T[Arrester unit and diode unit]- 60VDC or less for max. permissible circuit
voltage- DC or not more than 150kHz for frequency
band- Impulse protection performance* In common mode – Between a line andground~ Initial max value 350V or less
~ Max. value during operation 20V or less

* In normal mode – Between any two lines~ Initial max value 350V or less
~ Max. value during operation 20V or less
- 20kA for impulse current (at impulse
current waveform of 80/20μS)- Japanese notation

9. Flame monitoring system
UVS-05BN, UVS-06CN- Battery type (UVS-05BN)
24VDC wiring type (UVS-06CN)- Ultraviolet detector- Indoor type- High sensitivity detection distance of 4m(About 3cm lighter flame in front of thedetector)- Detection within 15 seconds

15- Wide viewing area (60° above and below
the horizontal surface of the sensor, 50° to
the left and right from the vertical surfaceof the sensor)- Multilingual voice alarm (Japanese,
English, Chinese, Korean)- Sound level of 80dB or more (at 1m infront of the sensor)

10. MiscellaneousProtector for heat & smoke detectors,
FZP012-L

Telephone hand set, SC-PA1

Detector tester for heat detector,
HK-3

Detector tester (Gas type) for smoke
detector, FTGW001-Z- Body, pole, bag and adaptor- Heating Cartridge selling
separately- Test gas selling separately

Detector tester for flame detector, FTEJ001-P- Recess mounting box- Powered by four AA batteries- Test distance within 20cm
- 0℃ 〜 40℃ ambient temperature (except dewfall)- Compatible with FDCJ002-D-X

Detector tester for IR3 flame detector, FTEJ002-P- Recess mounting box- Powered by four AA batteries- Test by closed range- 0℃ 〜 40℃ ambient temperature (except dewfall)- Compatible with FDCJ004-D, PDCJ001-D

Sensitivity measuring unit, FTDJ001-P- Powered by four AA batteries- 0℃ 〜 40℃ ambient temperature

Pole for tester, ZERJ002-15, 45, 60 & ZEAJ001- Three size available (1.5m, 4.5m, 6.0m)- Compatible with HK-3, FTGW001-Z, FTEJ001-P, FTEJ002-P

16

Foam fire extinguishing systems
Low to medium expansion foam fire extinguishing system
Data Sheet & Video

Low Expansion Foam System- Engineered System- P, AFFF, AR-AFFF foam type available- Low expansion foam system- Foam head, Foam nozzle, Foam chamber, Foam monitor system- Wide operating flow rate and less pressure loss proportioner available- Wide range of capacity foam tank available

MIDEX III- Self-contained manual type foam fire
extinguishing system- Indoor type
- AFFF foam type and S/AR foam typeavailable- Applicable fires: Class A and Class B fires- Discharge distance
Low expansion foam: Approx. 10m (at20℃) Medium expansion foam: Approx.
5m (at 20℃)

17

- Hose length 20m- Effective and fast-acting- Easy manual switching between low andmedium expansion foam
- Easy to use for a single person- No need for plumbing or electrical works- At least 70 seconds (at 20℃) for
discharge timeNitrogen gas fire suppression systems
1. Clean agent fire suppression systems & Components
Data Sheet & Video

NN100 gas suppression system- UL listed IG-100- Zero ozone depletion and zero global warming potential- No carbon dioxide and no halocarbons- Engineered type

NN100 package EX- Compact package unit
- Zero ozone depletion and zero global
warming potential- No carbon dioxide and no halocarbons- 220V to 240V±10%, 50/60Hz for AC input- Maximum room volume covered by one
storage cylinder
49m3 for Class A fire
39m3 for Class B and C fire

Noise reduction nozzle- Pendant and sidewall type available- Decreases impact on HDDs caused by thegas discharge noise- Easily replace existing nozzles- 90m3/min for nozzle flow rate
- Sound pressure level of 97dB (pendanttype), 99dB (sidewall type) on 1m away at
a 45° angle in front of the discharge point

Transparent gas discharge indicator- Sophisticated design- More visual impact when used Designed
to not be noticed until needed- Enhanced display for people with colorblindness- Multi-lingual support (Displayable up to
four languages)

2. Fire suppression system for object protection
750/1500/2250 CNF/TW- Gas output at ambient temperature- Non-pressurized nitrogen storage- Discharge sound level: Less than 99dB
with silencer (optional), 127dB withoutsilencer- No global warming potential- Low pressure gas release- Aspirating smoke detection (750/1500/
2250 CNF) Linear heat detection (750/
1500/2250 TW)- 110/230V for AC input- Flexible User Interface positioning- Back-up battery: 4 hrs (750/1500/2250
CNF), 12 hrs (750/1500/2250 TW)- Interconnectivity up to 8 systems- Maintenance free
- No residue clean up- Long shelf life18

“Nohmi Quality” you can trust

Specifications are subject to change without notice. Contact Nohmi before relying on the information.
Actual performance is based on proper application of the product by a qualified professional.
Should further information be required or should particular concerns arise that are not covered sufficiently for the
Purchaser’s purposes, the matter should be referred to Nohmi or your nearest distributor.

https://www.nohmi.co.jp/english/
Head Office: 4-7-3 Kudan-Minami, Chiyoda-ku, Tokyo 102-8277, Japan

Catalog Number 230630 B -F-2402YO1

The information contained herein does not purport to cover all the details or variations of the equipment described,
nor to provide for every possible contingency that may be met in connection with its installation, operation or,
maintenance.