Multicrest
fire alarm system

PCA-N3060-FIM2

TMN3060

Fiber-optic Interface Module 2Features• UL 864, 9th edition listed• Max. 64 nodes available on network• NFPA Style 4 & 7 connection applicable• Status LED• Single-mode optic fiber• Easy installation

Description
The PCA-N3060-FIM2 is the interface module for FACP networking to utilize fiber optic cable. The PCA-N3060-FIM2 is able to have the fiber optic
cable length 5km maximum, though the PCA-2707XA FIM can have the length 2km maximum.
The PCA-N3060-FIM2 consists of two boards, PCA-N3060-FIM2-A and PCA-N3060-FIM2-B. These boards shall be used together. ThePCA-N3060-FIM2 enables the system to use the Single-mode optic fiber system for the system network. The PCA-N3060-FIM2 is used in thesystem with the Network Interface Unit (PCA-2706XA NIU) and is mounted under the PCA-2706XA NIU inside the FACP cabinet.
The PCA-N3060-FIM2 contains an element by which the data from/to other FACPs on the network are converted to optical data for transmission.
The 24 VDC power required for operation is supplied from the Power Supply Unit (PCA-N3060-PSU) to the PCA-N3060-FIM2. The
PCA-N3060-FIM2 is equipped with a status indicator (LED). The green LED indicates normal 24 VDC power supply from the PCA-N3060-PSU
when it is turned on.

Ordering Information
Part No. PCA-N3060-FIM2-A, PCA-N3060-FIM2-B

Specifications
No.
123456789Item
Maximum 24 VDC standby current
Maximum 24 VDC alarm current
Ambient operating temperature range
Network connection style
Maximum number of node on network
Max. fiber length between an FIM2 and next FIM2Max. fiber length in total
Maximum attenuation ratio
Dimensions

Specification
74 mA
74 mA
0 to 49 °C (32 to 120 °F)
NFPA Style 4 or 764
5.0 km50.0 km5 dB
70 mm (H) x 70 mm (W) x 24 mm (D)Optic fiber specifications
No.
12345

Fiber type
Material
Core diameter
CladBandwidth

Item

SM
Quartz glass
9 µm
125 µm1310/1550 nm

Specification

Installation and Wiring Information

PCA-N3060SCU (No.1)

PCA-N3060PSU (No.1)

PCA-N3060SCU (No.2)
Cable P/N U-0011 S/M/L
AC/DC Switching
power supply unit

PCA-N3060SCU (No.3)
PCA-N3060SCU (No.4)
PCA-N3060SCU (No.5)

PCA-N3060PSU (No.2)

1+ 1- G
TB2
PortB

PCA-2706XA
NIU

PCA2706XA
NIU

J1

A
PCA-N3060-FIM2

AC/DC Switching
power supply unit

B

PCA-N3060-PSU

1+ 1- G
TB1
PortA

PCA-N3060SCU (No.6)

CNPF
PCA-N3060-SCU(No.1)

CN2

CN1+ -CN2+ -A

B

Battery

CN1

PCA-N3060-FIM2

Battery

NOTE
・The information contained herein does not purport to cover all the details or variations of the equipment described, nor to provide for every
possible contingency that may be met in connection with its installation, operation or maintenance.
・Specifications are subject to change without notice. Contact Nohmi before relying on the information.
・Actual performance is based on proper application of the product by a qualified professional.
・Should further information be required or should particular concerns arise that are not covered sufficiently for the purchaser’s purposes, thematter should be referred to Nohmi or your nearest distributor.

Contact• Head Office: 4-7-3 Kudan-Minami, Chiyoda-ku, Tokyo
102-8277, Japan• Phone: (81) 3 - 3265 - 0231
• F A X: (81) 3 - 3265 - 5348
URL http://www.nohmi.co.jp/english/

Catalog Number 131024Ⓓ-F-17400