Product Data Sheet
April 13th, 2020

LEDioc TUBE

EYE LEDioc TUBE offers energy savings for traditional fluorescent lighting
applications with no need for a comprehensive system change-out. Theform factor is equal to conventional fluorescent lamps providing
consistency of visual appearance for critical applications. EYE LED Tube is
an ideal solution for customers looking for a lower total cost ofownership with excellent lighting.
Performance Summary:

LED T8 LAMP

■Diverse color temperatures are available, including 3000K, 4000K & 6500K.
■High color rendering (Ra80), ensuring a vivid illumination.
■High luminous efficacy up to 150 ℓm/W (135 ℓm/W when 3000K).
■Long average life up to 40,000 hours (30,000 hours for flicker-free type).

❖Standard Type
Wattage

CCT

Luminous

Luminous Efficacy

LengthCircuitry

LDFLAC-1483018-T8/F
LDFLAC-1483018-T8/D/W/O
LDFLAC-1484021-T8/F
LDFLAC-1484021-T8/D/W/O
LDFLAC-1486521-T8/F
LDFLAC-1486521-T8/D/W/O

Model Number

14 W
14 W
14 W
14 W
14 W
14 W

3000 K
3000 K
4000 K
4000 K
6500 K
6500 K1890 ℓm
1890 ℓm
2100 ℓm
2100 ℓm
2100 ℓm
2100 ℓm

135 ℓm/W
135 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W

1200mm
1200mm
1200mm
1200mm
1200mm
1200mmSingle-ended
Double-ended
Single-ended
Double-ended
Single-ended
Double-ended

LDFLAC-1683021-T8/F
LDFLAC-1683021-T8/D/W/O
LDFLAC-1684024-T8/F
LDFLAC-1684024-T8/D/W/O
LDFLAC-1686524-T8/F
LDFLAC-1686524-T8/D/W/O

16W
16W
16W
16W
16W
16W

3000 K
3000 K
4000 K
4000 K
6500 K
6500 K

2160 ℓm
2160 ℓm
2400 ℓm
2400 ℓm
2400 ℓm
2400 ℓm

135 ℓm/W
135 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W

1200mm
1200mm
1200mm
1200mm
1200mm1200mm

Single-ended
Double-ended
Single-ended
Double-ended
Single-ended
Double-ended

LDFLAC-2083027-T8/F
LDFLAC-2083027-T8/D/W/O
LDFLAC-2084030-T8/F
LDFLAC-2084030-T8/D/W/O
LDFLAC-2086530-T8/F
LDFLAC-2086530-T8/D/W/O

20W
20W
20W
20W
20W
20W

3000 K
3000 K
4000 K
4000 K
6500 K
6500 K

2700 ℓm
2700 ℓm
3000 ℓm
3000 ℓm
3000 ℓm
3000 ℓm

135 ℓm/W
135 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W

1200mm
1200mm
1200mm
1200mm
1200mm
1200mmSingle-ended
Double-ended
Single-ended
Double-ended
Single-ended
Double-ended

LDFLAC-2483032-T8/F
LDFLAC-2483032-T8/D/W/O
LDFLAC-2484036-T8/F
LDFLAC-2484036-T8/D/W/O
LDFLAC-2486536-T8/F
LDFLAC-2486536-T8/D/W/O

24W
24W
24W
24W
24W
24W

3000 K
3000 K
4000 K
4000 K
6500 K
6500 K

3240 ℓm
3240 ℓm
3600 ℓm
3600 ℓm
3600 ℓm
3600 ℓm

135 ℓm/W
135 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W

1500mm
1500mm
1500mm
1500mm
1500mm
1500mmSingle-ended
Double-ended
Single-ended
Double-ended
Single-ended
Double-ended

Common Specifications:■Bulb: T8■Input Voltage: 220~240V■Protection Grade: IP20

■Base: G13■Service Temperarure: -20~45°C■Material: Glass + PET■CRI : > Ra80
■Life Span: 40,000 hrs■Power Factor: >0.9
■Beam Angle: >160°■Certification & Coformity: CE(not include double-ended models), RoHS

❖Flicker-Free Type
Model Number
LDFLBC-1684024-T8/F
LDFLBC-1684024-T8/D/W/O
LDFLBC-1686524-T8/F
LDFLBC-1686524-T8/D/W/O

Common Specifications:■Bulb: T8■Input Voltage: 220~240V■Protection Grade: IP20

Wattage

CCT

Luminous

Luminous Efficacy

LengthCircuitry

16W
16W
16W
16W

4000 K
4000 K
6500 K
6500 K

2400 ℓm
2400 ℓm
2400 ℓm
2400 ℓm

150 ℓm/W
150 ℓm/W
150 ℓm/W
150 ℓm/W

1200mm
1200mm
1200mm
1200mmSingle-ended
Double-ended
Single-ended
Double-ended■Base: G13■Service Temperarure: -20~45°C■Material: Glass + PET■CRI : > Ra80
■Life Span: 30,000 hrs■Power Factor: >0.9
■Beam Angle: >160°■Certification & Coformity: CE(not include double-ended models), RoHS

Product Data Sheet
April 13th, 2020
Dimensions

ModelAB

CD

Weight

14W, 16W, 20W

1200 mm

1206.5 mm

1213.6 mm

26 mm

215 g

24W

1500 mm

1506.5 mm

1513.6 mm

26 mm

300 g

Wiring Instructions-When Repalcing Fluorescent LampsI. Remove the existing fluorescent lamp ballast
1. Turn off switch before re-installation
2. Take off the lamp and ballast.(refer to “figure 1”)

ACFluorescent Lamp
BallastII. Install the LEDioc TUBE
3. Connect the wiring to the lamp holder.(refer to “figure 2” )4. When using the single-ended models, please check themarking on the lamp end, and install the LEDioc TUBE with AC
mains supplied to the end marked.
5. Make sure the lamp has been securely installed, turn onthe switch.

Fluorescent Lamp
【figure 1】-When Directly Installing the LED lamps1. Connect the wiring to the lamp holder. (refer to “figure 2” )2. When using the single-ended models, please check themarking on the lamp end, and install the LEDioc TUBE with AC
mains supplied to the end marked.
3. Make sure the lamp has been securely installed, turn onthe switch.

NoticeDO NOT use the product in the following locations.
・ Outdoor environment.
・ Indoor environment existing corrosive gases,
flammable gases or oil mist.

ACLEDioc TUBE<Single-Ended>ACLEDioc TUBE
<Double-Ended>【figure 2】

1-1-7, Higashi-Nihonbashi, Chuo-ku, Tokyo 103-0004, Japan
Website: http://www.eye.co.jp
Tel.: +81-3-5846-9010