CAT. NO.

D -F-20100

LOCATION LAMPFLPJ SERIESFEATURES● Cutting-edge new design● Noticeable red color● Low current and high durability● Low-voltage operation● Wide and high visibility● Non-combustible and self-extinguishing materials● Outdoor type available

FLPJ002(W)

DESCRIPTIONNOHMI s high-performance location lamps model
FLPJ002(W) and FLPJ004(W) are used for, but notlimited to, notifying occupants of the location of amanual ﬁre alarm box.
The location lamps were designed based on a newconcept considering functionality, accessibility, andusability. Thanks to the new design concept, thering-shaped location lamp FLPJ004(W) won the Japan
Good Design Gold Award 2014 together with thecompact-shaped FMMN, FMRN, and FMBN SERIES
manual ﬁre alarm boxes.
The location lamp FLPJ004(W) is installed together
with the compact manual ﬁre alarm box, which isFLPJ004(W)positioned around the manual alarm box so that theexact location of the manual alarm box can be foundeven in dark places. The ﬂat-shaped location lampFLPJ002(W) should be installed on the wall just above
a manual ﬁre alarm box, to be clearly seen at a position
within 10 meters from the location lamp.
These location lamps without using any fragile
materials are provided with a red LED lamp per unit asa light source, which has light-emitting diodes in it.
These location lamps can be repeatedly turned on andoﬀ within a short interval of time to indicate the hydrant
pump starting by using together with the NOHMI
hydrant pump starter relay box.

SPECIFICATIONSMODEL NO.

FLPJ002

FLPJ002-W

FLPJ004

FLPJ004-W

USE SPECIFICATIONS

IndoorOutdoorIndoorOutdoor

LIGHT SOURCERed LED lamp
20 to 35VDC/AC15mA−10 to 50℃

RATE VOLTAGE
RATED CURRENTAMBIENT TEMPERATURE

Polycarbonate resin (self-extinguishable)

MAIN MATERIALWEIGHT

Approx. 57g

Approx. 66gApprox. 92g

Approx. 93g●HEAD OFFICE：7-3, Kudan-Minami 4-chome, Chiyoda-ku, Tokyo 102-8277, Japan ●PHONE：（81）3-3265-0231 ●FAX：（81）3-3265-5348

LOCATION LAMP FLPJ002 & FLPJ004 SERIES

CAT. NO.

D -F-20100

TYPICAL WIRING DIAGRAM
Connection of location lamp to fire alarm control panel

PUPUPVPV

Location lamp
FLPJ002(W), FLPJ004(W)Fire alarm control panel

DIMENSIONSFLPJ002(W)

FLPJ004(W)
RAINPROOF PACKING(OUTDOOR TYPE ONLY)

GLOBE (RED, TRANSPARENT)

φ92

BODY

TERMINAL

RING-SHAPEDLOCATION LAMPAPERTURE

BACK COVER(WHITE)RAINPROOF PACKING(OUTDOOR TYPE ONLY)TERMINAL COVER(BLACK)

R2.9

3.5

128

33.4
36.9

17.

1
28.5

14.4

96

69

128

66.7(a)59.5

BODY(TRANSPARENT RED)

96

INSTALLATIONFLPJ002(W)

FLPJ004(W)Rainproof packing for the manualfire alarm box

FRONT7366.7

MOUNTING WITH
RECESS BOXTYPICAL INSTALLATION WITH
MANUAL FIRE ALARM BOX

BACK VIEW

Manual fire alarmbox and ring-typepilot lamp

27.

φ48

73

11φ

14.4

800〜1500

R2.556.

FRONT VIEW
(VIEW WITHOUT GLOBE)

124.6

Mounting screws

9673

R2.5

11φ9.5

8.6

66.7
φ48
116.6

66.7

APERTURE

14.4

１40
MOUNTING WITH
SURFACE BOX

96

Mounting sheet metal(rear side)

4-M4×L12 STUDS

Flange nuts

PANEL PROCESSING DRAWING(BACK VIEW)● These instructions do not purport to cover all the details or variations in the equipment described, nor provide for every possible contingency to be met inconnection with installation, operation, and maintenance.

● Speciﬁcations are subject to change without notice. Contact NOHMI before relying on the above speciﬁcations.
● Actual performance is based on proper application of the product by a qualiﬁed professional.

● Should further information be desired or should particular problems arise, which are not covered suﬃciently for the purchaser's purposes, the matter should

be referred to NOHMI or a distributer in your region.

●HEAD OFFICE ： 7-3, Kudan Minami 4-chome,Chiyoda-ku, Tokyo 102-8277, Japan●PHONE：（81）
3-3265-0231●F A X：（81）3-3265-5348●U R L： http://www.nohmi.co.jp/english/160510 D -F-20100YO1