CAT. NO.

D -F-18504

FWLN SERIESCOMBINATION BOXFeatures• Three-in-one (location lamp, manual fire alarm box, and fire alarm bell)• Cutting-edge new design• Addressable type available• Surface and recess mountings available• Easy installation

Description
The combination box consists of a location lamp, a manual fire alarm box, and a fire
alarm bell, designed based on a new concept considering functionality, accessibility,and usability.
The ring-shaped location lamp is positioned around the manual alarm box so that the exact location of the manual alarm box can be found even in darkplaces. Thanks to the new design concept of the ring-shaped location lamp with the manual alarm box, which won the Japan Good Design Gold Award
2014, the surface depth is only 15mm in recess mounting and 75mm in surface mounting.
The physical structure of this well-designed three-in-one product makes the wiring very easy when installed.

Specifications
Surface mounting
Recess mounting
MODEL NO. OF PLATE
MODEL NO. Surface mounting
OF BOX
Recess mounting
MODEL NO.

FWLN007A-R-P1
FWLN007A-U-P1
ZBPN007A-P1

FWLN007A-R-P1W
FWLN007A-U-P1W
ZBPN007A-P1W

ConventionalIndoor use

USE SPECIFICATIONSFWLN007A-R-P1DW
FWLN007A-U-P1DW
ZBPN007A-P1DW
ZBRJ003A-T
ZBCJ006-T

Conventional
Rain proof。
。
−10 C to +40 C
90dB or more (at 1m)

AMBIENT TEMPERATURE
SOUND LEVELMANUAL ALARM
LAMP
BELL

DIMENSIONS

Addressable
Rain proof

FMMN102-UW

FMBN102-U

FMBN102-UW

FLPJ004

FLPJ004-W

FLPJ004
FBMJ001-D

FLPJ004-W

FBMJ001

RECESS MOUNTING① Acoustic holes(75)151515185

FMMN102-U

SURFACE MOUNTING

156060② Fixing screw
7651火災報知機

94215

158.6

強く押す1095〜1790mm

41094380

21110〜1805mm

9483Addressable
IndoorBaking finish for plate and surface mounting box, color equivalent to Munsell N8.7, semi-gloss
Black paint for recess mounting box

FINISH

15FWLN007A-R-ADW
FWLN007A-U-ADW
ZBPN007A-ADW

1.2mm steel sheet for plate and surface mounting box
1.6mm steel sheet for recess mounting box

MAIN MATERIALS OF
PLATE AND BOX

CONTAINED

FWLN007A-R-AD
FWLN007A-U-AD
ZBPN007A-AD

76.3

76.3

③ Location lamp (ring-shaped)④ Manual alarm box⑤ Plate⑥ Surface mounting box⑦ Recess mounting box⑧ Audible device (alarm bell)⑨ Terminals (12P)Tipical Wiring Diagram
CONVENTIONAL SYSTEMADDRESSABLE SYSTEMFOR USE WITH φ0.5〜2.0mm WIRE
PU
PV

LOCATION
LAMP

FIRE
ALARM
CONTROLPANEL＋PU

−PV−

BC
BF
(or Kn)ADDRESSABLE
MODULEWET OUTPUT

S＋S−

END-OF-LINE
RESISTOR R
10kΩ,1/2W

〜L1＋

ALARM
BELL

−

ADDRESSABLE
FIRE
ALARM
CONTROLPANELMANUALALARM BOX

FIRE
DETECTOREND-OF-LINE
RESISTOR
10kΩ,1/2W＋LOCATION
LAMP

R

ALARM
BELL

Ln
CA
T

24VDC

S−S＋

MANUALALARM BOXLOCATION LAMP FLPJ SERIESDIMENSIONS
59.5

BODY
(TRANSPARENT RED)

96BODY

9612866.7116.6

RING-SHAPEDLOCATION LAMPAPERTURE

BACK COVER(WHITE)RAINPROOF PACKING(OUTDOOR TYPE ONLY)

R2.93.533.4
36.9

17.

128

FIRE ALARM BELL FBMJ SERIESMANUAL FIRE ALARM BOX FMMN / FMBN SERIESDIMENSIONSDIMENSIONS
Φ1303856.6

COVER PLATE
JACK COVER

8.6

φ100

BODY

TERMINAL
COVER

PUSH BUTTONSWITCHRESPONSE LAMPACRYLIC PLASTIC COVER

800〜1500

7.649GONG

NOTE・The information contained herein does not purport to cover all the details or variations of the equipment described, nor to provide for every
possible contingency that may be met in connection with its installation, operation or maintenance.
・Specifications are subject to change without notice. Contact Nohmi before relying on the information.
・Actual performance is based on proper application of the product by a qualified professional.
・Should further information be required or should particular concerns arise that are not covered sufficiently for the purchaser’s purposes, thematter should be referred to Nohmi or your nearest distributor.

Contact• Head Office: 4-7-3 Kudan-Minami, Chiyoda-ku, Tokyo
102-8277, Japan• Phone: (81) 3 - 3265 - 0231
• F A X: (81) 3 - 3265 - 5348
URL https://www.nohmi.co.jp/english/

Catalog Number 240210Ⓓ-F-18504MS01