取 扱 説 明 書
形式：ＣＳＡ－１０９－Ｔ
品名：デマンド監視装置

２０２３年７月１２日

Ｔ－５５１７１改訂５

目次

１． はじめに ....................................................................................................................................................... 4
２． 商標について ................................................................................................................................................ 4３． 端末機器技術基準適合認定および特定無線設備の技術基準適合証明等 ......................................................... 4
４． ご注意 ........................................................................................................................................................... 5
４－１． 安全上のご注意......................................................................................................................................... 5
４－２． 使用上のご注意......................................................................................................................................... 8
５． 機器構成 ....................................................................................................................................................... 9
５－１． 構成一覧 ................................................................................................................................................... 9
５－２． 形式枝番 ................................................................................................................................................. 10
５－３． 専用 CT について ................................................................................................................................... 10
６． 本体各部の名称と働き ................................................................................................................................. 11
６－１． 装置前面 ................................................................................................................................................. 11
６－２． 装置端子カバー内 ................................................................................................................................... 12
６－３． 端子台信号内容....................................................................................................................................... 13
６－４． 装置上面及び銘板貼付位置 .................................................................................................................... 13
７． 設置方法 ..................................................................................................................................................... 14
７－１． 端子カバーの取り外し ............................................................................................................................ 14
７－２． 取り付け ................................................................................................................................................. 14
７－３． 配線 ......................................................................................................................................................... 15

７－３－１． 配線の注意 ................................................................................................................................... 15
７－３－２． 電源の接続 ................................................................................................................................... 15
７－３－３． LTE 通信アンテナの接続 ............................................................................................................ 15
７－３－４． 入力端子台への接続 .................................................................................................................... 16
７－３－５． 制御線の接続 ............................................................................................................................... 19
７－３－６． RS-232C 通信線の接続 ............................................................................................................... 20
７－３－７． RS-485 通信線の接続 .................................................................................................................. 20
７－３－８． 中継器の設置 ............................................................................................................................... 21
８． 運転前の準備と運転開始 ............................................................................................................................. 23
８－１． 運転前の準備 .......................................................................................................................................... 23
８－２． 運転開始 ................................................................................................................................................. 24
９． 通常モード .................................................................................................................................................. 25
９－１． 通常モード画面一覧 ............................................................................................................................... 25
９－２． 通常モード画面詳細 ............................................................................................................................... 26
１０． 設定・テスト・USB 操作 ........................................................................................................................ 31
１０－１． 設定・テスト・USB 操作画面一覧 .................................................................................................... 31
１０－２． システム設定....................................................................................................................................... 32
１０－３． 警報設定 .............................................................................................................................................. 34
１０－４． 計測設定 .............................................................................................................................................. 37
１０－５． 通信設定 .............................................................................................................................................. 39

１０－５－１． RS-232C・RS-485 ポート１・RS-485 ポート２通信設定 ...................................................... 40
１０－５－２． PLC 通信（電力線通信）設定 ................................................................................................. 41
１０－５－３． Ethernet 通信設定 ................................................................................................................... 43
１０－６． テストモード....................................................................................................................................... 45
１０－７． USB メモリの操作（計測データ：出力、設定値：入出力）............................................................. 47
１１． 特殊操作モード ....................................................................................................................................... 54
１１－１． 特殊操作モード画面一覧 .................................................................................................................... 54
１１－２． ソフトウェアアップデート ................................................................................................................. 55

Ｔ－５５１７１改訂５－2－

１１－３． 電力量表示の値設定 ............................................................................................................................ 56
１１－４． オールリセット（初期化） ................................................................................................................. 57
１１－５． Web サーバ初期化 .............................................................................................................................. 58
１１－６． 装置再起動 .......................................................................................................................................... 59
１２． Web サーバ機能 ...................................................................................................................................... 60
１２－１． はじめに .............................................................................................................................................. 60
１２－２． 準備 ..................................................................................................................................................... 60
１２－３． Web アクセスする .............................................................................................................................. 60
１２－４． Web 画面詳細 ...................................................................................................................................... 61
１３． CSV フォーマット詳細 ............................................................................................................................ 69
１３－１． ファイル名 .......................................................................................................................................... 69
１３－２． フォーマット....................................................................................................................................... 69
１４． 外形寸法図 .............................................................................................................................................. 71
１５． 使用条件 .................................................................................................................................................. 78
１６． お手入れについて .................................................................................................................................... 79
１ ７ ． 保 管 に あ た っ て ................................................................................................................................ 79
１８． 保証期間と保証範囲 ................................................................................................................................ 79
１ ９ ． お 問 い 合 わ せ .................................................................................................................................... 79

Ｔ－５５１７１改訂５－3－

１．はじめに
このたびは、「デマンド監視装置」をお買い上げ頂きまして、ありがとうございます。
この取扱説明書は、安全にご使用いただくための重要な注意事項と、基本的な取り扱い方法などを記載したものです。
この取扱説明書をよくお読みの上、正しく安全にお使いください。
お読みになった後は大切に保管し、必要な時にお読みください。
装置の仕様、演算などのソフトウェア仕様については、「仕様書」をご参照ください。

※ 本書の内容を無断で転載することを堅くお断りいたします。
※ 製品の改良などにより、本書の内容に一部合致しないことがあります。

２．商標について下記の他社登録商標または商標をはじめ、本書に記載されている会社名、システム名、製品名は一般に各社の登録商標または商標です。
なお、本文および図表中では、「™」、「®」は明記しておりません。
・LTE は、欧州電気通信標準協会（ETSI）の登録商標です。
・Google Chrome は米国 Google Inc.の米国およびその他の国における登録商標または商標です。
・Microsoft、Windows、WindowsXP、WindowsVista、Windows7、Windows8、Windows10、Word、Excel および Microsoft のロゴは、米国およびその他の国における Microsoft Corporation
および/またはその関連会社の登録商標または商標です。
・ Java お よ び す べ て の Java 関 連 の 商 標 、 Solaris お よ び そ れ ら の ロ ゴ は 、 米 国 Sun
Microsystems, Inc.の米国およびその他の国における登録商標または商標です。

３．端末機器技術基準適合認定および特定無線設備の技術基準適合証明等
本製品が LTE 通信機能付きの場合、下記が適応されます。
（１）端末機器技術基準適合認定
本製品には、電気通信事業法第 56 条第 2 項の規定に基づく端末機器の設計について認定を受けた以下の設備が組み込まれております。
・機器名称：UM04-KO、認証番号：D15-0201001（２）特定無線設備の技術基準適合証明等
本製品には、特定無線設備の技術基準適合証明等に関する規則 第 2 条第 1 項第 11 号の 3,7 および 19 に規定される以下の設備が組み込まれております。
・機器名称：UM04-KO、工事設計認証番号：001-A06417

Ｔ－５５１７１改訂５－4－

４．ご注意４－１．安全上のご注意
製品を安全にご使用いただくための注意事項が記載されています。
ご使用の前にこの「安全上のご注意」を必ずお読みになり、注意事項を守ってご使用ください。
製品を安全に正しくご使用頂き、ご使用になる人や他の人への危害や財産への損害を未然に防止するため、次の表示を使用して説明しています。
表示内容を無視して誤った使い方をしたときに生じる危害や損害の程度を次の絵表示で区分し、説明しています。

警告
注意

この表示事項を無視して、誤った取り扱いをすると、人が死亡または傷を負う可能性が想定される内容を示しています。
この表示事項を無視して、誤った取り扱いをすると、人が傷害を負う可能性が想定される内容、および、物的損害の発生が想定される内容を示しています。

誤った取り扱いによって、感電の可能性が想定されることを示しています。
安全の為、電源コードのプラグを必ず抜くように指示するものです。

誤った取り扱いによって、発煙または発火の可能性が想定されることを示しています。
安全の為、アース線は必ず接続するように指示するものです。

お守り頂く内容の種類を次の絵表示で区分し、説明しています。

このような絵表示は、してはいけない「禁止」内容です。

このような絵表示は、必ず実行していただく「強制」内容です。

Ｔ－５５１７１改訂５

－5－

警告
●ＡＣ１１０Ｖ（６０または５０Ｈｚ）の使用
異なる電圧で使用すると、感電、発煙、火災発生の恐れがあります。

●電源コードを引っ張らない
電源コードを傷つけたり、コード上に重いものを乗せたり、無理に曲げたり、コードを引っ張ったり、加熱したりしないでください。
感電、火災発生の恐れがあります。

●水をかけない
水類や薬品がこぼれた場合、感電、火災発生の恐れがあります。

●金属物を入れない
金属物が入った場合、感電、火災発生の恐れがあります。

●上に物を置かない
ケースの上に物を置きますと、筐体が変形し損傷の原因となります。

●落とさない落としたりして強い衝撃を与えると、感電、火災発生の恐れがあります。

●分解、改造しない
分解、改造をすると、感電、火災発生の恐れがあります。

●濡れた手で触らない
濡れた手で触ったり、電源プラグを抜き差しすると感電する恐れがあります。

●タコ足配線はしない
タコ足配線にするとコンセントが加熱し、火災発生の恐れがあります。

●電源プラグは確実に差し込む
電源プラグの端子に金属などが触れると、感電、火災の原因になる恐れがあります。

●活線状態で端子部に手を触れない感電する恐れがあります。

Ｔ－５５１７１改訂５

－6－

警告
●アース線を接続する
アース線は必ず接続してください。接続してあるアース線は外さないでください。
万一漏電した場合に、感電、火災発生の恐れがあります。

万一、本装置を落としたり、ケースを破損したりした場合は、電源プラグをコンセントから抜いて、販売店にご連絡ください。
そのまま使用すると、感電、火災発生の恐れがあります。

万一、内部に水などが入った場合は、すぐに電源プラグをコンセントから抜いて、販売店にご連絡ください。そのまま使用すると、感電、火災発生の恐れがあります。

内部の点検、修理は、弊社営業にご依頼ください。

注意●高温・多湿のところに置かない
直射日光のあたるところや湿度の高いところに置かないでください。
故障、感電の恐れがあります。

●不安定な場所に置かない
落下、転倒により、けがをすることがあります。

●コードを持って引き抜かない
電源プラグを抜くときは、コードを引っ張らないで、必ずプラグ本体を持って抜いてください。
電源プラグのコードを引っ張り抜くと、感電、火災発生の恐れがあります。

Ｔ－５５１７１改訂５－7－

４－２．使用上のご注意（１）初めてのご使用時は必ず時計および設定値の設定を行ってください。
停電時も日時は約 3 ヶ月自動歩進しますが、長期にわたり通電しない場合、日時は正常な値を表示しません。再設定を行ってください。
（２）納入品の故障、又はお客様の故意・過失・誤用・異常な条件でのご利用によって誘発される損害に関して、弊社は一切責任を負いませんので、予めご了承ください。
（３）本装置の PLC(電力線通信機能)をご使用になる場合は、デマンドモニターやデマンド警報装置と同じトランス、同じ相になるように設置ください。
（４）本装置の Ethernet 通信機能をご使用になる場合は、IPv4 の固定 IP アドレスが必要です。
ご使用となるネットワークの管理者とご相談の上、適切な値を設定ください。
（５）本装置の専用 CT(標準タイプ・長距離タイプ)を設置される場合、以下の内容をご確認のうえ、設置ください。
①大電流が流れるケーブルからは、専用 CT を可能な限り離してください。
専用 CT は、微弱な電流によるパルス信号を検出しています。そのため幹線等、大電流が流れるケーブル近傍に専用 CT を設置されますと、磁界の影響によりパルス信号正常に検出できなくなる場合があります。設置の際には、可能な限りケーブルから専用 CT を離して設置ください。
②大電流が流れるケーブルに対し、専用 CT の配置方向に注意してください。
図.1、図.2、図.3 のように、大電流が流れるケーブルに対し、専用 CT のクランプ用コアの平面を垂直方向に設置されますと、専用 CT は磁界の影響を受けます。
クランプ用コア(平面)
電力量計接続線

ケーブル断面ケーブル

クランプ用コア(上平面)
図.2 ケーブルに対し垂直に設置した専用 CT (真上 1)
クランプ用コア(平面)ケーブル断面

クランプ用コア(下平面)
図.1 ケーブルに対し垂直に設置した専用 CT(真横)図.3 ケーブルに対し垂直に設置した専用 CT (真上 2)

図.4、図.5 のようにケーブルに対し専用 CT を水平方向に設置することで、磁界の影響を緩和することができます。平面は上下どちらでも磁界の影響を緩和することができます。
ケーブル
クランプ用コア(平面)

電力量計接続線

図.4 ケーブルに対し水平に設置した専用 CT(真横)ケーブル

クランプ用コア(平面)
図.5 ケーブルに対し水平に設置した専用 CT(3D)

Ｔ－５５１７１改訂５－8－

５．機器構成
５－１．構成一覧
内容

形式

数量

CSA-109-T

1台

デマンドモニター（RS-485 タイプ）

CSA-109-D2-R

オプション

デマンドモニター（Ethernet タイプ）

CSA-109-D2-E

オプション

TDD3ZB-R

オプション

デマンド警報装置(デマンド警報 3 点)

TDD3ZB-R-X1

オプション

中継装置（PLC 用、3 台まで使用可）

TDD3ZB-W

オプション

LoRa 無線機

HLR-RS485

オプション

デマンド監視装置

デマンド警報装置(デマンド警報 2 点、機器異常警報 1 点)

専用 CT 標準タイプ(4m ケーブル付き、延長不可)

CT-S1

専用 CT 長距離タイプ(ケーブル無し、100m 以内で使用)

CT-L1

専用 CT 長距離タイプ用接続ケーブル（長さを指定してください）

CB62-□

電力量計接続線

CB59

電源ケーブル(3m、L 型プラグ)

CB67

USB メモリオプション(次ページ参照)

専用 CT 1 個につき1 本付属
装置 1 台につき
1 本付属

-

オプション

帳票出力用テンプレートファイル収録 CD-ROM

TPS-31-T

オプション

FOMA アダプタ用小型防滴アンテナ（全てのユビキタスモジュールにおいて共通）

-

オプション
（LTE 通信機能有り時に、2 本必要）

※ 上記オプション品は標準では付属されませんので、別途手配ください。
※ 取引用計器からパルス信号を取込む場合、専用 CT が必要です。
専用 CT については次ページ「専用 CT について」をご参照ください。
※ USB メモリの形式・容量・メーカについては、在庫及びメーカからの供給状態によって変わります。都度ご確認ください。

Ｔ－５５１７１改訂５－9－

５－２．形式枝番

ＣＳＡ－１０９－Ｔ－ ① ② ③ ④①通信機能
無記号：LTE 通信機能無し
Ｌ：LTE 通信機能有り※ 通信プロトコルについては別途お打ち合わせの上、規定するものとします。
②計測機能
Ｐ：パルス入力（電力量パルス、時限パルスの取り込み）※ 無記号にした場合、「Ｐ」を指定したものとして扱います。
③取付け方法無記号：マグネット無し
Ｍ：マグネット有り（背面 3 箇所に磁石を装着）④特殊仕様指定
無記号：標準仕様

５－３．専用 CT について
CT を使用してパルス信号を取り込む場合は下記 CT を別途ご発注ください。
専用 CT 長距離タイプをご使用される場合は専用 CT 長距離タイプ用接続ケーブルを合わせて、ご指定ください。
オープンコレクタ出力を持つ機器（パルス変換器など）から信号を取り込む場合、CT は不要です。
形式
ＣＴ－Ｓ１

ＣＴ－Ｌ１

用途
短距離での電力量パルス
または時限パルスの取り込み
配線距離 4m 以内でご使用ください※ ケーブル延長不可

内容
専用 CT 標準タイプ：1 個
電力量計接続線：1 本
結束バンド：1 本
4m ケーブル付

4m を超える距離での電力量パルス
または時限パルスの取り込み※ 配線距離 100m 以内でご使用ください。

専用 CT 長距離タイプ：1 個
電力量計接続線：1 本
ショートピン：1 個
結束バンド：1 本
ケーブル無専用 CT 長距離タイプと本装置間の接続ケーブル□の部分は長さ 5m または 10～100m を 10m 単位でご指 専用 CT 長距離タイプ用
ＣＢ６２－□ 定ください
接続ケーブル：1 本※ 例
長さ：5m～100m（指定）CB62-10：10m
CB62-30：30m
CB62-100：100m
屋外で配線する場合は、ノイズ対策及び雷対策を行ってください。
また、電力量パルスと時限パルスを両方取り込む場合は、ケーブルを 2 本に分けてください。
多芯ケーブルでまとめた場合、干渉する恐れがあります。
標準タイプ・長距離タイプともに、ケーブルは動力線から 50cm 以上の距離をあけて配線してください。
雷に対しては金属配管などで保護してください。
Ｔ－５５１７１改訂５－10－

６．本体各部の名称と働き
６－１．装置前面①液晶表示器②異常ランプ③電源ランプ④設定中ランプ⑤電力量ランプ⑥電界強度ランプ（LTE 通信機能有りの場合のみ搭載）⑩USB 端子(メモリ専用)⑦制御出力ランプ⑧操作ボタン（左・右・決定・取消）⑨端子カバー① 液晶表示器（LCD）
動作状況や設定値などの表示を行います。

⑦ 制御出力ランプ
制御出力が ON で、対応したランプが点灯します。

② 異常ランプ装置に異常を検出した場合、点滅します。

⑧ 操作ボタン
表示項目の切り替えや設定に使用します。

③ 電源ランプ
装置電源 ON で点灯します。

⑨ 端子カバー
配線や PLC の搬送周波数の切替の際、このカバーを開けます。

④ 設定中ランプ
設定値変更中に点滅します。

⑩ USB 端子USB メモリ専用の端子です。記録データの出力などに使用します。

⑤ 電力量ランプ
電力量パルスの検出状態により、点滅します。
⑥ 電界強度ランプ
下記の仕様で動作します。
ランプの状態

内容

全て消灯

LTE モジュールの電源 OFF
LTE モジュール設定中※起動後は必ず LTE モジュール設定を行います。
※起動から LTE モジュール設定完了まで約 1 分かかります。
※設定中に一度 LTE モジュールを再起動します。
SIM カードがない
または、通信が圏外状態で待機
通信レベル 1（アンテナ 1 本）で待機（パケット非通信状態）
通信レベル 2（アンテナ 2 本）で待機（パケット非通信状態）
通信レベル 3（アンテナ 3 本）で待機（パケット非通信状態）

全て点滅（500ms）

圏外点灯
■点灯
■■点灯
■■■点灯
圏外～■■■のいずれか 1 つが早い点滅（200ms）
圏外～■■■のいずれか 1 つがゆっくり点滅（500ms）
圏外～■■■のいずれか 1 つが2 連点滅（500ms 毎 2 回 ON、1 秒 OFF）

Ｔ－５５１７１改訂５

該当の通信レベルで着信中または発信中
該当の通信レベルで回線接続処理中
該当の通信レベルでオンライン状態－11－

６－２．装置端子カバー内①メンテ用端子③ RS-232C 通信端子
⑤ Ethernet 通信端子
② LCD 輝度調整
④ SIM カードソケット ※⑥ LTE 通信モジュール ※

ＴＢ１

ＴＢ３

ＴＢ２

⑦ 電源端子台⑨ 出力及び RS-485 通信端子台⑧ 入力端子台※ LTE 通信機能有りの場合にのみ搭載⑩PLC 周波数切替スイッチ
1 側：7.5kHz 2 側：9kHz① メンテ用端子
当社工場内でのメンテナンス時に使用する端子です。
② LCD 輝度調整
LCD の見え具合を調整する場合に使用します。

③ RS-232C 通信端子
別売の専用通信ケーブルで PC などの通信機器と接続するための端子です。
④ SIM カードソケット
LTE 通信機能有りの場合に搭載します。LTE 通信用 SIM カードを入れるソケットです。
⑤ Ethernet 通信端子
LAN ケーブル及び既設の LAN 回線を使用して通信するための端子台です。
⑥ LTE 通信モジュール
LTE 通信機能有りの場合に搭載します。LTE 通信の制御を行うモジュールです。
⑦ 電源端子台
電源及びアース線の接続を行うための端子台です。
⑧ 入力端子台
電力量パルスや時限パルス信号を入力するための端子台です。
⑨ 出力及び RS-485 通信端子台
制御出力及び RS-485 通信用の配線を行うための端子台です。
⑩ PLC 周波数切替スイッチ
電力線通信の搬送周波数を切り替えるためのスイッチです。
通常は、スイッチを 2 側にしてご使用ください。
Ｔ－５５１７１改訂５－12－

６－３．端子台信号内容※ 専用 CT 長距離タイプを接続する場合や、無電圧パルス・オープンコレクタ出力機器を接続する場合は、標準入力（k、l）はショートしてください。

６－４．装置上面及び銘板貼付位置①LTE アンテナ接続端子
左：Main 右：Sub
背面側

正面側

*

Rev.*
*

記銘板
※ 製造番号は YYMMSSSS の構成
YY：西暦年下 2 桁、MM：月、SSSS：連番※ Rev.*（*はハードの改訂番号）※ No.3478*（*は銘板の改訂番号）① LTE アンテナ接続端子
LTE 通信機能有りの場合に搭載します。
通信アンテナのケーブルを接続します。

Ｔ－５５１７１改訂５－13－特定無線設備の技術適合証明等※ LTE 通信機能有りの場合にのみ、貼付されます※ No.3480*（*は銘板の改訂番号）

７．設置方法
７－１．端子カバーの取り外し（１）図に示す部分を指で押さえます。

（２）手前に引きます。

引く
７－２．取り付け（１）ネジで取り付ける場合
M3mm ネジを装置の取り付けフック穴と端子カバー内のネジ穴に差し込み、固定します。
M3mm ネジで固定（２）マグネットで取り付ける場合
本装置を磁石取り付け可能な面へ、ゆっくりと取り付けてください。

ゆっくり

ゆっくり

Ｔ－５５１７１改訂５－14－

７－３．配線
７－３－１．配線の注意
・配線完了するまで、電源を ON にしないでください。
・接続にあたり、以下の圧着端子をご使用ください。

3.2mm 以上

絶縁チューブ6mm 以下圧着端子部は、使用する電線のサイズに合わせてください。
・接続終了後は、必ず端子カバーを取り付けてください。
・入力線と出力線の接続は、装置本体及び関連機器を屋内で使用することを前提にしています。
入力線または出力線が屋外を経由する場合は、雷サージなどの影響を回避するためのサージ吸収素子（避雷器など）を取り付けてください。

７－３－２．電源の接続
・装置下部左側の電源端子台（TB2）に付属のケーブルを接続します。
・1 番左の端子はアースです。D 種接地してください。
装置下部端子台

補助電源
AC100V

７－３－３．LTE 通信アンテナの接続・装置付属のアンテナをご使用ください。付属アンテナ以外のアンテナは動作保証外です。
・ケーブル類の引き回しは、コネクタに無理な力がかからな
いように余裕をもたせてください。
・ケーブル類を伝わる水滴が装置内部に侵入しないように、コネクタ近くでいったんコネクタより下方にケーブル類を引き回してください。
・左側が「Main」、右側が「Sub」端子となります。

Ｔ－５５１７１改訂５－15－

７－３－４．入力端子台への接続
端子下部中央の入力端子台(TB1)に、CT またはパルス変換器の出力ケーブルを接続します。
（１）専用 CT 標準タイプを使用する場合
・CT ケーブルの圧着端子部と装置の端子台には、「k」「ℓ」のマーキングがありますので、下図の「k」「ℓ」に合うように接続してください。
・同期信号を使用しない場合は、何も接続しないでください。
・ケーブルは動力線から 50cm 以上の距離をあけて配線してください。
CT ケーブルの「k」側を接続
電力量パルス用 CT ケーブル
CT ケーブルの「ℓ」側を接続

装置下部端子台CT ケーブルの「ℓ」側を接続
同期信号用 CT ケーブル
CT ケーブルの「k」側を接続（２）専用 CT 長距離タイプを使用する場合
・接続ケーブルには専用の専用 CT 長距離タイプ用接続ケーブル「CB62」をご使用ください。
・CT 下部の端子カバーを開け、下図の様に CT 底部の記号とケーブルマークチューブの記号を合わせて配線してください。
※ 圧着端子の挿入方向に注意してください。
・専用 CT 標準用の端子はショートしてください。
・同期信号を使用しない場合は、何も接続しないでください。
・ケーブルは動力線から 50cm 以上の距離をあけて配線してください。
・雷に対しては金属配管などで保護してください。
CT 底部

R0

ﾊﾟﾙｽ

R1

R1

GND

OUT－GND－DC12V

R0

12V

端子カバー

12

圧
着
端
子
入
線
方
向

12V

GND

ﾊﾟﾙｽ

12V

電力量パルス用 CT ケーブル

装置下部端子台

GND

ﾊﾟﾙｽ

12V

Ｔ－５５１７１改訂５

同期信号用 CT ケーブル
－16－

付属のショートピンで、ショートしてください・専用 CT 長距離タイプ用接続ケーブル加工
専用 CT 長距離タイプ用接続ケーブル「CB62」をご使用にならない場合、推奨ケーブルに下記の加工を行った上で接続してください。
推奨ケーブル：
シールド付き 1 対（2 芯）ツイストペア線
0.75mm2 (株)フジクラ製 IPEV-S 弱電計装ケーブル相当品
接続例：
専用 CT
長距離タイプ
端子
12V
R1
R0

デマンド監視装置
電力量パルス入力
端子
12V ﾊﾟﾙｽ GND
シールド付き 1 対 ツイストペア線

シールド線

シールド線

加工例：
ツイストペア線のシールドと導線を半田付けしてください。
導線を痛めないように、内部導線からシールドを浮かせて半田付けしてください。
※シールド及び、内部導線を傷つけないように注意してください。
0.75mm 導線

フェライトコア(E04SR200935AB)

絶縁チューブ80
25

Y 型圧着端子
GND
ﾊﾟﾙｽ
12V
ツイストペア内部導線(白色)

ツイストペア線シールド
収縮チューブ（点線）
シールド付き 1 対 ツイストペア線

ツイストペア内部導線(青色)結束バンドで導線 3 本を束ねる（３）電力量計接続線の接続
専用 CT 標準タイプ、または長距離タイプに電力量計接続線を接続する場合、下記の手順で接続
してください。
①センサ両側のレバーを軽く押してセンサ頭部を上に引き上げて開口します。
②接続線を中心部の溝に沿って、電力量計接続線を通します。
③センサ頭部を元の位置に戻し、爪がカチッと音がするまで下に押し込んだ後、爪が浮いていないことを確認します。
④爪とレバーの間を付属の結束バンドにより、開口部が開かないように、固定します。
センサ頭部

センサ頭部を上に引上げてから開口！

接続線を通す注意爪

電力量計接続線通線後結束バンドで固定

レバー

Ｔ－５５１７１改訂５

結束バンドを
強く締め付け過ぎるとケースが破損する恐れがあります。

－17－

（４）無電圧パルスまたはオープンコレクタ出力機器を使用する場合
・端子台への接続は 0.75 mm2～1.25mm2 2 芯ケーブルをご使用ください。
・本装置に外部オープンコレクタ出力機器を接続する場合、本装置の GND 端子をエミッタ側
端子に、本装置のパルス端子をコレクタ側端子に接続してください。
・無電圧パルス出力機器を接続する場合、極性はありませんので、どちらに接続してもかまいません。
・屋外配線する場合、シールド付き 2 芯ケーブルをご使用ください。
・ケーブルは動力線から 50cm 以上の距離をあけて配線してください。
・雷に対しては金属配管などで保護してください。
・専用 CT 標準タイプ用端子をショートしてください。（下図参照）
RS-485 通信端子を使用しない場合、ショートピンを取り外し、付け替えて頂くこともできます。
ショートしてください
装置下部端子台

RS-485 通信端子を使用しない場合、取り外して流用可能

配線例①他社製オープンコレクタ出力機器
外部ｵｰﾌﾟﾝｺﾚｸﾀ
出力機器
出力端子
ｺﾚｸﾀ
ｴﾐｯﾀ

デマンド監視装置
電力量パルス入力
端子
12V ﾊﾟﾙｽ GND②弊社製パルス出力形電力量センサ（出力端子：電線差し込み式）
・対応機種：TWP-X5 など
・ケーブル：0.75mm2 撚線
パルス出力形
電力量センサ
出力端子89＋Ｔ－５５１７１改訂５

デマンド監視装置
電力量パルス入力
端子
12V ﾊﾟﾙｽ GND

－

－18－

③弊社製パルス出力形電力量センサ（出力端子：RJ-45）・対応機種：TWPD、TWP-X8 など
・ケーブル：パルス出力形電力量センサ専用のパルス出力ケーブル「CB71」をご使用ください。
・ケーブル長：約 5m
パルス出力形
電力量センサ
出力端子
出力ｺﾈｸﾀデマンド監視装置
電力量パルス入力
端子
12V ﾊﾟﾙｽ GND

パルス:青
パルス出力ケーブル「CB71」

GND：オレンジ

７－３－５．制御線の接続・制御出力端子 D1～D4 はそれぞれ無電圧 a 接点で出力されます。
・COM 端子は全て共通です。
・接点容量：AC100V、120mA（抵抗負荷）
・ON 抵抗：35Ω以下
・ケーブルは動力線から 50cm 以上の距離をあけて配線してください。
・雷に対しては金属配管などで保護してください。

端子の割当①デマンド監視モードが「シンプル２段階」の場合

D1
D2
D3
注意
限界
機器異常
※ COM 端子は共通です

D4
予備②デマンド監視モードが「シンプル３段階」の場合

D1
D2
D3
注意
警戒
限界
※ COM 端子は共通です

Ｔ－５５１７１改訂５

D4
機器異常

－19－

７－３－６．RS-232C 通信線の接続・接続には専用のパソコン用通信ケーブル「CB68」をご使用下さい。
・ケーブル長：約 1.7m
・ケーブルは動力線から 50cm 以上の距離をあけて配線してください。

デマンド監視装置
RS-232C 通信端子

パソコン
RS-232C コネクタ
タ

パソコン用通信ケーブル「CB68」

７－３－７．RS-485 通信線の接続
・0.75mm2～1.25mm2 シールド付き 2 芯ケーブルをご使用ください。
・端子には極性がありますので、接続の際は注意してください。
・ケーブルのシールドは全て SL（SG）端子に接続し、1 箇所で D 種接地してください。
もし、接地がとれない場合は接地しないでください。
・RS-485 通信線への接続は一筆書きとなるようにしてください。
・本装置が RS485 通信線の末端となる場合は RS+端子と Ter 端子間は付属のショートピンでショートしてください。
・RS-485 通信端子 1 へ接続する場合、ケーブル長は 1000m 以下とし、ケーブルは動力線から 50cm
以上の距離をあけて配線してください。
・雷に対しては金属配管などで保護してください。
・RS-485 通信端子 2 は屋内配線のみとし、ケーブルは動力線から 50cm 以上の距離をあけて配線してください。

デマンド監視装置

E

Ter

RS-485 通信端子
RS+ RS－ SL

RS-485 端末機
RS+

RS－

SL

ショートピン

シールド付き 2 芯ケーブル
D 種接地

Ｔ－５５１７１改訂５－20－

RS-485 端末機
RS+

RS－

SL

７－３－８．中継器の設置
通信距離が 100m を越える場合や、
電灯線ラインのノイズ等で通信エラーが発生する場合の対策として、通信途中に中継措置を最大 3 台まで設置可能です。
（１）取り付け例：中継装置 1 台の場合
デマンド監視装置

中継装置

デマンド警報装置

100m 以内

デマンド表示器100m 以内① 中継器は、デマンド監視装置とデマンド警報装置（またはデマンド表示器）の間に設置します。
② デマンド監視装置・中継器・デマンド警報装置及びデマンド表示器の電源接続相は、一致させてください。

Ｔ－５５１７１改訂５－21－

（２）中継装置のモードスイッチ設定
No.
1
2
3
4
5
6

機能
バンド選択
アドレス 20
アドレス 21
不使用 ※テストモード不使用 ※バンド切替スイッチ

出荷時設定
OFF
OFF
OFF
OFF
OFF
OFF

モードスイッチ※ 不使用のスイッチは、OFF のままでご使用ください。
①バンド選択搬送周波数を変更する場合は、モードスイッチの No.1 とバンド切替スイッチを下記の様に切り替えてください。
搬送周波数
9kHz の場合（出荷時設定）
7.5kHz の場合

モードスイッチ
No.1：バンド選択
OFFON

バンド切替スイッチ「9kHz」側「9kHz」の反対側②アドレス設定
中継装置の台数によって、下記の様に中継装置のアドレス設定を行います。
中継装置
モードスイッチ No.
状態

1 台目
2
3
OFF
OFF

2 台目
2
3
ON
OFF

中継装置 1 台のみ使用の場合
中継装置 2 台使用の場合
中継装置 3 台使用の場合③テストモード
No.5 を ON にすると、テスト用の搬送波を出力します。
通常使用時は、No.5 を OFF のままでご使用ください。

Ｔ－５５１７１改訂５

－22－

3 台目
2
3
OFF
ON

中継装置のモードスイッチ
2

3

８．運転前の準備と運転開始
設置後初めて運転を開始する場合、必ず時刻校正及び各種設定を行ってください。
ここでは、その手順を示します。

８－１．運転前の準備（１）装置の電源を ON にする装置の電源端子に AC100Ｖを印加すると、電源が ON になり、バージョン表示します。
その後、約 3 秒で時計表示になります。
形式
バージョン表示ソフトウェアバージョン番号

CSA-109-T VX.XX
50.0Hz

電源周波数

約３秒後
時計表示

12:34:56 1234kW
ﾖｿｸ 1234kW（２）時刻校正する装置が時計表示をしている状態で、下記操作を行い、装置の時計表示が電力量計の時計と同じ時刻になるように校正します。
途中、操作を間違えた場合、取消ボタンを押すことで、時計表示画面に戻ることができます。
時計表示

12:34:56 1234kW
ﾖｿｸ 1234kW

ﾆﾁｼﾞ ｾｯﾃｲ *2013/01/23 12:34

決定
決定
設定メニューｼｽﾃﾑ ｾｯﾃｲ
ﾆﾁｼﾞ ｾｯﾃｲ
2013/01/23 12:34
決定

日時設定

時刻全てが点滅し、設定待機状態になります。
決定ボタンにて、0 秒から歩進開始します。

ﾆﾁｼﾞ ｾｯﾃｲ
2013/01/23 12:34
決定

ﾆﾁｼﾞ ｾｯﾃｲ
2013/01/23 12:34

変更する部分が点滅するので、
右・左ボタンで数値を変更します。
決定ボタンで隣の項目が点滅します。

「分」変更後に決定ボタン

Ｔ－５５１７１改訂５－23－

時刻校正完了です。
取消ボタンにて、時計表
示に戻します。

（３）各種設定を行う「１０．設定・テスト・USB 操作」（31 ページ）をご参照いただき、設定値を登録します。
通信を行わない場合、通信設定は不要です。

８－２．運転開始
時刻の校正及び設定値の登録が終われば、使用準備完了です。
下記を確認してください。
① 設定中ランプが消灯していること② 異常ランプが消灯していること③ 時計表示の値が、電力量計に一致していること④ 電力量ランプが、点滅していること
以上、問題なければ、運転開始です。
「９．通常モード」（25 ページ）をご参考いただき、各種データをご確認ください。

Ｔ－５５１７１改訂５－24－

９．通常モード
９－１．通常モード画面一覧
通常モード時、取消ボタンを押すと、時計表示に戻ります。
右・左ボタンで、各項目を切り替えます。
①バージョン表示
左CSA-109-T VX.XX
50.0Hz②時計表示

12:34:56 1234kW
ﾖｿｸ 1234kW③契約番号表示ｹｲﾔｸNo.
[]④シリアル番号表示
決定

ｼﾘｱﾙNo. 12-34-56
78-9A-BC

設定メニューへ⑤瞬時電力表示ｼｭﾝｼﾞ ﾃﾞﾝﾘｮｸ
1234kW⑥入力パルス表示

Whﾊﾟﾙｽ
0p/secﾄﾞｳｷｼﾝｺﾞｳ
0ｶｲ⑦当月最大値表示

ﾄｳｹﾞﾂ ｻｲﾀﾞｲ
1234kW⑧電力量表示ﾃﾞﾝﾘｮｸﾘｮｳ
12345678kWh⑨最大デマンド表示

MAX01 2014/01/20
11:00
1234kW

電力量表示(kWh 以下表示)

決定ﾃﾞﾝﾘｮｸﾘｮｳ.12345kWh決定
決定を押す毎に順に表示（1 位～10 位）
取消長押し
最大デマンドクリア確認画面を表示⑩月別積算電力量表示

ｾｷｻﾝ01

01ｶﾞﾂﾄﾞ
123456kWh

決定
決定を押す毎に順に表示（前月度から１年分）⑪装置状態表示右ｿｳﾁ ｼﾞｮｳﾀｲｲｼﾞｮｳ ﾅｼ

Ｔ－５５１７１改訂５

決定
決定を押す毎に順に表示（複数の異常発生時）－25－

９－２．通常モード画面詳細①バージョン表示
装置の形式、バージョン番号、電源周波数の計測状態を表示します。
PLC を使用する設定の場合は、搬送周波数の設定状態も表示します。
装置の形式

バージョン番号

CSA-109-T VX.XX
9.0kHz50.0Hz
電源周波数（1 秒毎に更新）
搬送周波数設定状態
PLC を使用する設定の場合にのみ表示
装置下部取り外し可能フタ内のスイッチの状態を表示します②時計表示
装置の時刻、現在デマンド、予測デマンドを表示する画面です。
現在時刻（時：分：秒）

12:34:56 1234kW
ﾖｿｸ 1234kW

現在デマンド(現在電力)
予測電力③契約番号表示装置に設定した契約番号を表示します。

ｹｲﾔｸNo.
[DAT0123456]

設定した契約番号を表示④シリアル番号表示
装置のシリアル番号を表示します。
Ethernet での通信時や、USB メモリへのファイル出力時に使用します。
装置毎にユニークな 16 進数の番号です。
（製造番号とは異なりますので、ご注意ください）

ｼﾘｱﾙNo. 12-34-56
78-9A-BC⑤瞬時電力表示
入力パルスから演算した瞬時電力値(30 秒間分のパルスから演算した換算値)を表示します。

ｼｭﾝｼﾞ ﾃﾞﾝﾘｮｸ
1234kW

Ｔ－５５１７１改訂５－26－

⑥入力パルス表示
入力パルスの状態を表示します。
上段には電力量パルス(Wh パルス)の入力状況を「パルス／秒」の単位で表示します。
下段には同期信号パルスの入力状況を回数で表示します。

Whﾊﾟﾙｽ
0p/secﾄﾞｳｷｼﾝｺﾞｳ G 2ｶｲ

電力量パルス入力状態
同期信号パルス入力回数

電源 ON 時または同期信号受付後、ガードタイマが動作中は、「G」を表示します。
電力量パルスの入力状態について表示値が 14p/sec を超えるようであれば、入力パルスにノイズが入っている可能性があります。
端子入線部のｋとｌが間違えていないかなど、ご確認ください。

同期信号パルスの入力回数について「G」を表示しているとき、同期信号の入力端子でパルスを検出すると、回数は増えますが、時刻校正はしません。
同期信号タイミングでないのに回数が増える場合は、ノイズが入っている可能性があります。
端子入線部のｋとｌが間違えていないかなど、ご確認ください。
表示回数は、電源 ON 時または、99 回を超えると、0 に戻ります。
電源 ON 直後 30 秒間は「G」表示をし、ガードタイマが動作します。

⑦当月最大値表示
当月（装置の時計が１日～現在時刻に至るまで）の最大デマンド電力を表示します。
月が変わった直後の 0 時 29 分 59 秒までは、前月に計測した値を表示します。

ﾄｳｹﾞﾂ ｻｲﾀﾞｲ
1234kW⑧電力量表示電力量のカウント値を表示します。
カウント値が、99999999kWh を超える場合、再び 0kWh からカウントします。

ﾃﾞﾝﾘｮｸﾘｮｳ
12345678kWh
この画面において、決定ボタンを押すと、kWh 以下を表示する画面に切り替えます。

ﾃﾞﾝﾘｮｸﾘｮｳ.12345kWh
小数点Ｔ－５５１７１改訂５

小数点以下 5 桁までを表示－27－

⑨最大デマンド表示
記録した最大デマンド値（上位 10 データ）を決定ボタンを押す毎に順次表示します。
上位 10 以内に同じ値のデマンド電力値がある場合は、記録年月日および記録時間の新しい方が上位になります。
記録年月日、記録時間は、デマンド時限の終了時刻で記録します。
例：8 月 10 日の 10：00～10：30 に計測した値が最大デマンド値だった場合、8 月 10 日 10：30のデータとして記録します。
順位 01～10（01 が最大値）

記録年月日

MAX01 2014/01/20
11:00
1234kW

記録時間

記録したデマンド電力値

最大デマンドデータのクリア操作
最大デマンド表示のとき、取消ボタンを長押しすると、最大デマンド値のクリア確認画面を表示します。
この画面において下記の操作を行うと、記録した上位 10 データをクリアします。

MAX01 2014/01/20
11:00
1234kW

最大デマンド表示

取消長押し

MAX01 ｶﾗ MAX10
ｸﾘｱｼﾅｲ

クリア確認画面

決定ボタンを押すと、点滅します
点滅中、右・左ボタンで表示を「ｸﾘｱｽﾙ」に切り替えます
表示が「ｸﾘｱｽﾙ」になっているときに、決定ボタンを押します
表示が「ｸﾘｱｽﾙ」の時に決定を押す

MAX01 ｶﾗ MAX10
ｸﾘｱ ｼﾏｼﾀ

クリア完了表示
この表示になれば、クリア完了です
取消ボタンを押すと、時計表示に戻ります

Ｔ－５５１７１改訂５－28－

⑩月別積算電力量表示
検針日毎に記録した積算電力量を、決定ボタンを押す毎に順次表示します。
現在計測中の月の前月から順に表示します。
例：現在６月度分を計測中の場合、５月度から順に４月、３月・・・・６月を表示。
表示番号（前月から順に 01～12）

記録月度

ｾｷｻﾝ 01 12ｶﾞﾂﾄﾞ
123456kWh
記録月度の積算電力量

月別積算電力量の記録間隔について
月別積算電力量は、「検針日」設定に基づき記録します。
例：検針日を１日に設定した場合
検針日が１日の場合、「7 ｶﾞﾂﾄﾞ」と表示する時の積算電力量は、６月１日０時０分０秒から６月３０日２３時５９分５９秒までを計測した値となります。
６月１日０：００

７月１日０：００
７月分の値

例：検針日を１５日に設定した場合
検針日が１５日の場合、「7 ｶﾞﾂﾄﾞ」と表示する時の積算電力量は、６月１５日０時０分０秒から７月１４日２３時５９分５９秒までを計測した値となります。
６月１５日０：００

７月１５日０：００
７月分の値

Ｔ－５５１７１改訂５－29－

⑪装置状態表示
装置が機器異常を検出していればその状態を表示します。
複数の異常状態が発生している場合、決定ボタンを押す毎に順次表示します。

ｿｳﾁ ｼﾞｮｳﾀｲｲｼﾞｮｳ ﾅｼ
正常時「ｲｼﾞｮｳﾅｼ」を表示
機器異常発生時、異常の種類を表示（下記参照）
機器異常の出力内容について（１）ﾉｰﾊﾟﾙｽ ｴﾗｰ
電力量パルス信号が一定時間を超えて入力されなかった場合に出力します。
検出までの時間は、設定により変更可能です。
（２）ﾄｹｲ ﾃﾞｰﾀ ｴﾗｰ
長期の停電などで、装置の時計データが異常になっている場合に出力します。
このエラーを検出した場合は、時計を再設定してください。
（３）ﾄｹｲ IC ｴﾗｰ
装置の時計 IC に異常を検出した場合に出力します。
（４）LCD ｴﾗｰ
装置の液晶表示器に異常を検出した場合に出力します。
（５）LAN IC ｴﾗｰ
装置の Ethernet を制御する IC に異常を検出した場合に出力します。
（６）USB ｴﾗｰ
装置の USB 制御回路に異常を検出した場合に出力します。
（７）ｼｭｳﾊｽｳ ｴﾗｰ
電源周波数 50Hz または 60Hz の±3Hz を外れた場合に出力します。
（８）EEPROM ｴﾗｰ
装置の内部メモリに異常を検出した場合に出力します。
（９）FeRAM ｴﾗｰ
装置の内部メモリに異常を検出した場合に出力します。
（１０）LTE ﾓｼﾞｭｰﾙ ｴﾗｰ
装置内部の LTE 通信モジュールに異常を検出した場合に出力します。

Ｔ－５５１７１改訂５－30－

１０．設定・テスト・USB 操作
１０－１．設定・テスト・USB 操作画面一覧
時計表示の画面にて、決定ボタンを押すと、設定メニュー画面を表示します。
各設定メニュー画面にて、決定ボタンを押すと、設定項目の画面を表示します。

時計表示

12:34:56 1234kW
ﾖｿｸ 1234kW
決定取消①システム設定②警報設定
右ｼｽﾃﾑ ｾｯﾃｲ

⑥へ
左

取消

決定
日時設定
電力量パルス設定
外部同期信号設定
デマンド監視モード設定
契約 No 設定
ノーパルスエラー待ち時間設定

③計測設定

右

ｹｲｿｸ ｾｯﾃｲ
左④通信設定

ﾂｳｼﾝ ｾｯﾃｲ

左CT 比設定合成変成比設定
補正係数設定検針日設定
最大デマンドリセット設定

左

取消

右

ﾃｽﾄ ﾓｰﾄﾞ

RS-232C 通信設定
RS-485 ポート１通信設定
RS-485 ポート２通信設定
PLC 通信設定
Ethernet 通信設定

⑥USB 操作USB ｿｳｻ

①へ
右

左
決定

決定

データ出力
設定値入出力バックアップ／復元

制御出力テストランプテスト
PLC テスト
取消

取消

Ｔ－５５１７１改訂５⑤へ

決定⑤テストモード④へ取消

注意電力設定警戒電力設定限界電力設定マスク時間設定
ON ホールドタイマ設定
OFF ホールドタイマ設定
警報マスク時間帯設定

右

決定

取消

③へ
右

左
決定

②へ

ｹｲﾎｳ ｾｯﾃｲ－31－

１０－２．システム設定
右・左ボタンにて項目を変更します。
各設定画面において、決定ボタンを押すと、設定値が点滅し、値の変更が可能になります。
（このとき、設定中ランプが点滅します。）
もう一度決定ボタンを押すと、設定中ランプ及び設定値の点滅が止まり、設定値が保存されます。
設定中のとき、取消ボタンを押すと、設定を中止します。
設定中でないとき、取消ボタンを押すと、上位の画面に戻ります。

ｼｽﾃﾑ ｾｯﾃｲ
決定

左

右

取消

ﾆﾁｼﾞ ｾｯﾃｲ
2013/01/23 12:34①日時設定

ﾃﾞﾝﾘｮｸﾘｮｳ ﾊﾟﾙｽ
ﾋｮｳｼﾞｭﾝ CT②電力量パルス設定

ｶﾞｲﾌﾞ ﾄﾞｳｷ ｼﾝｺﾞｳ
ｼﾖｳｼﾅｲ③外部同期信号設定

ﾃﾞﾏﾝﾄﾞ ｶﾝｼ ﾓｰﾄﾞ
ｼﾝﾌﾟﾙ 2ﾀﾞﾝｶｲ④デマンド監視モード

ｹｲﾔｸNo. ﾍﾝｺｳ[

⑤契約番号設定]

ﾉｰﾊﾟﾙｽｴﾗｰ ﾏﾁｼﾞｶﾝ
0600ﾋﾞｮｳ

⑥ノーパルスエラー待ち時間設定①日時設定
装置本体の時計を設定する画面です。
決定ボタンを押すと、設定項目及び設定中ランプが点滅します。
右・左ボタンにて、値を変更します。
取消ボタンを押すと、設定を中止します。
決定ボタンを押す毎に、設定中項目が年→月→日→時→分の順に切り替わります。

ﾆﾁｼﾞ ｾｯﾃｲ
2013/01/23 12:34
設定中の項目が点滅します。右・左ボタンで値を変更します。
「分」の設定後、決定ボタンを押すと、画面上段に「＊」を表示し、時刻データ全体が点滅します。

ﾆﾁｼﾞ ｾｯﾃｲ *2013/01/23 12:34

マークを表示時刻データ全体が点滅

このとき、決定ボタンを押すと、時刻データ確定し、0 秒から歩進開始します。

Ｔ－５５１７１改訂５－32－

②電力量パルス設定
装置の電力量パルス取り込み方法を設定する画面です。
決定ボタンを押すと、設定項目及び設定中ランプが点滅します。
右・左ボタンにて、値を変更します。
取消ボタンを押すと、設定を中止します。

ﾃﾞﾝﾘｮｸﾘｮｳ ﾊﾟﾙｽ
ﾋｮｳｼﾞｭﾝ CT「ﾋｮｳｼﾞｭﾝ CT」：専用 CT 標準タイプ「ﾁｮｳｷｮﾘ CT」：専用 CT 長距離タイプ「ﾑﾃﾞﾝｱﾂ ﾊﾟﾙｽ」：無電圧パルスまたはオープンコレクタ③外部同期信号設定
装置の外部同期信号取り込み方法を設定する画面です。
決定ボタンを押すと、設定項目及び設定中ランプが点滅します。
右・左ボタンにて、値を変更します。
取消ボタンを押すと、設定を中止します。

ｶﾞｲﾌﾞ ﾄﾞｳｷ ｼﾝｺﾞｳ
ｼﾖｳｼﾅｲ「ｼﾖｳｼﾅｲ」：外部同期信号端子への入力を受け付けません。
「ﾋｮｳｼﾞｭﾝ CT」：専用 CT 標準タイプ「ﾁｮｳｷｮﾘ CT」：専用 CT 長距離タイプ「ﾑﾃﾞﾝｱﾂ ﾊﾟﾙｽ」：無電圧パルスまたはオープンコレクタ④デマンド監視モード
デマンドの警報出力方法を設定する画面です。
決定ボタンを押すと、設定項目及び設定中ランプが点滅します。
右・左ボタンにて、値を変更します。
取消ボタンを押すと、設定を中止します。

ﾃﾞﾏﾝﾄﾞ ｶﾝｼ ﾓｰﾄﾞ
ｼﾝﾌﾟﾙ 2ﾀﾞﾝｶｲ「ｼﾝﾌﾟﾙ 2 ﾀﾞﾝｶｲ」：シンプル２段階
デマンド警報を注意警報・限界警報の２段階で出力します。
「ｼﾝﾌﾟﾙ 3 ﾀﾞﾝｶｲ」：シンプル３段階
デマンド警報を注意警報・警戒警報・限界警報の３段階で出力します。

⑤契約番号設定
契約番号として、管理用の番号を設定する画面です。
契約番号を使用しない場合、特に設定する必要はありません。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。（スペース、ハイフン、英大文字、数字が設定可能）
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ｹｲﾔｸNo. ﾍﾝｺｳ
[DAT0000012]

Ｔ－５５１７１改訂５

10 桁の管理番号を一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

－33－

⑥ノーパルスエラーﾏﾁｼﾞｶﾝ設定
電力量パルスの入力がないとき、ここで設定した時間が経過すると、ノーパルスエラーとなります。
0 秒に設定すると、ノーパルスエラーの判定を行いません。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。
一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

ﾉｰﾊﾟﾙｽｴﾗｰ ﾏﾁｼﾞｶﾝ
0600ﾋﾞｮｳ

１０－３．警報設定
右・左ボタンにて項目を変更します。
各設定画面において、決定ボタンを押すと、設定値が点滅し、値の変更が可能になります。
（このとき、設定中ランプが点滅します。）
もう一度決定ボタンを押すと、設定中ランプ及び設定値の点滅が止まり、設定値が保存されます。
設定中のとき、取消ボタンを押すと、設定を中止します。
設定中でないとき、取消ボタンを押すと、上位の画面に戻ります。

ｹｲﾎｳ ｾｯﾃｲ
決定

左

取消

ﾁｭｳｲ ﾃﾞﾝﾘｮｸ
12345kW
ｹｲｶｲ ﾃﾞﾝﾘｮｸ
12345kW②警戒電力設定※ デマンド監視モードが「ｼﾝﾌﾟﾙ 3 ﾀﾞﾝｶｲ」のときに表示

ｹﾞﾝｶｲ ﾃﾞﾝﾘｮｸ
12345kW③限界電力設定

ﾏｽｸ ｼﾞｶﾝ

④マスク時間設定30ﾌﾝ

右①注意電力設定

ON ﾎｰﾙﾄﾞ ﾀｲﾏ
0000ﾋﾞｮｳ

⑤ON ホールドタイマ設定

OFF ﾎｰﾙﾄﾞ ﾀｲﾏ
0000ﾋﾞｮｳ

⑥OFF ホールドタイマ設定

ｹｲﾎｳ ﾏｽｸ ｼﾞｶﾝﾀｲ
00ｼﾞ ｶﾗ 00ｼﾞ

⑦警報マスク時間帯設定

Ｔ－５５１７１改訂５－34－

①注意電力設定②警戒電力設定③限界電力設定
各警報を出力するための基準値を設定します。
計測中のデマンド電力が、ここで設定した値のラインを上回ると、該当の制御出力が ON になります。
または、ここで設定した値のラインを下回ると、該当の制御出力が OFF になります。
警戒電力設定画面は、デマンド監視モードを「ｼﾝﾌﾟﾙ 3 ﾀﾞﾝｶｲ」に設定した場合に表示します。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。
「ﾁｭｳｲ」
・「ｹｲｶｲ」・「ｹﾞﾝｶｲ」を表示
一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

ﾁｭｳｲ ﾃﾞﾝﾘｮｸ
12345kW電力

デマンド電力が設定値を下回った

注意または警戒または限界
電力設定値
デマンド電力デマンド電力が設定値を上回った

０分

３０分
ON

時間

OFF

該当の制御出力④マスク時間設定
デマンド時限開始直後、すぐに警報出力しないようにするための時間を設定します。
デマンド時限開始後、ここに設定した時間が経過するまでは、デマンド警報（注意警報・警戒警報・
限界警報）の出力をしません。
30 分に設定すると、デマンド警報の出力をしません。
機器異常警報は、この設定値の影響を受けません。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。
1～30 分で設定します。

ﾏｽｸ ｼﾞｶﾝ
30ﾌﾝ

Ｔ－５５１７１改訂５－35－

⑤ON ホールドタイマ設定
デマンド警報出力後、出力 ON の状態を保持させるためのタイマです。
ここで設定した時間が経過するまでは、デマンド警報は出力 OFF しません。
機器異常警報は、この設定値の影響を受けません。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ON ﾎｰﾙﾄﾞ ﾀｲﾏ
0000ﾋﾞｮｳ

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

⑥OFF ホールドタイマ設定
デマンド警報が出力 OFF になった後、出力 OFF の状態を保持させるためのタイマです。
ここで設定した時間が経過するまでは、デマンド警報は出力 ON しません。
機器異常警報は、この設定値の影響を受けません。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

OFF ﾎｰﾙﾄﾞ ﾀｲﾏ
0000ﾋﾞｮｳ

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

⑦警報マスク時間帯設定
日々のデマンド計測において、警報を出力しない時間帯を設定します。
設定した開始「時」と終了「時」の間は、デマンド警報及びノーパルスエラーの出力をしなくなります。
（機器異常警報は出力します）
開始「時」と終了「時」を同じ値に設定すると、本設定値は不使用となります。
警報出力中に設定変更した場合は、次のデマンド時限または一度警報が出力 OFF になった後から有効になります。
決定ボタンを押すと、左側の設定値が点滅します。開始「時」を設定ください。
右・左ボタンにて、値を変更します。
開始「時」を設定後、決定ボタンを押すと、右側の設定値が点滅します。終了「時」を設定ください。
終了「時」が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ｹｲﾎｳ ﾏｽｸ ｼﾞｶﾝﾀｲ
00ｼﾞ ｶﾗ 00ｼﾞ
開始「時」

Ｔ－５５１７１改訂５

終了「時」

－36－

１０－４．計測設定
右・左ボタンにて項目を変更します。
決定ボタンを押すと、設定値が点滅し、値の変更が可能になります。
（このとき、設定中ランプが点滅します。）
もう一度決定ボタンを押すと、設定中ランプ及び設定値の点滅が止まり、設定値が保存されます。
設定中でないとき、取消ボタンを押すと、上位の画面に戻ります。

ｹｲｿｸ ｾｯﾃｲ
決定

取消

CTﾋ
20A/5A左ｺﾞｳｾｲﾍﾝｾｲﾋ
00000
ﾎｾｲ ｹｲｽｳ
1.00
ｹﾝｼﾝﾋﾞ
01ﾆﾁ
右MAX01ｶﾗMAX10ﾘｾｯﾄ
ｼﾞﾄﾞｳ①CT 比設定②合成変成比設定③補正係数設定④検針日設定⑤最大デマンドリセット設定①CT 比設定
デマンド電力を計測するための、CT 比を設定します。
電力量計や変換器と同じ値に設定ください。
本設定値を使用して計測する場合は、合成変成比をゼロに設定してください。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

CTﾋ
20A/5A②合成変成比設定
CT 比を使用せずにデマンド電力を計測する場合は、本設定値を設定します。
本設定値をゼロに設定すると、CT 比を使用した計測になります。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ｺﾞｳｾｲﾍﾝｾｲﾋ
00000

Ｔ－５５１７１改訂５

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

－37－

③補正係数設定
電力量変換器を使用した場合に、電力量計との誤差がある場合は、本設定値を調整します。
補正する必要のない場合は、初期値の「1.00」でご使用ください。
本設定値を使用すると、計測した電力量パルスからデマンド電力や電力量を演算するときに、演算結果に対して設定した値を乗算します。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ﾎｾｲ ｹｲｽｳ
1.00

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

④検針日設定デマンド監視装置は月別の積算電力量を記憶しており、この画面で設定した検針日を区切りとして記録されます。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。
1～28 日で設定します。

ｹﾝｼﾝﾋﾞ
01ﾆﾁ⑤最大デマンドリセット設定
デマンド監視装置が記録した最大デマンド上位 10 データのリセット方法を変更します。
自動・手動を設定することができ、設定値により下記の動作をします。

設定値
ｼﾞﾄﾞｳ（自動）ｼｭﾄﾞｳ（手動）動作
リセット操作または最大値更新されるまでデータ保持。
また、記録後１年経過したデータは、自動的に削除。
（次年度の同じ月に削除します）
一度記録したデータは、リセット操作または最大値更新されるまでデータ保持。

決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

MAX01ｶﾗMAX10ﾘｾｯﾄ
ｼﾞﾄﾞｳ

Ｔ－５５１７１改訂５－38－

１０－５．通信設定
右・左ボタンにて項目を変更します。
決定ボタンを押すと、各通信端子の設定項目を表示します。
取消ボタンを押すと、上位の画面に戻ります。

ﾂｳｼﾝ ｾｯﾃｲ

通信設定表示決定取消①RS-232C 通信設定
⑤へ
左②RS-485 ポート１通信設定
右RS-232C
ﾐﾆｼﾞｬｯｸ

左局番(アドレス)設定
通信速度設定通信パラメータ設定
通信モード設定取消③RS-485 ポート２通信設定②へ
左RS-485 ﾎﾟｰﾄ 2
ﾀﾝｼﾀﾞｲ ﾐｷﾞ

右左左Ethernet
RJ-45 ｼﾞｬｯｸ④PLC 通信設定

PLC
AC100V ﾀﾝｼ

取消

①へ
右

決定
IP アドレス設定
マスクビット設定
ゲートウェイ設定
取消

Ｔ－５５１７１改訂５

局番(アドレス)設定
通信速度設定通信パラメータ設定
通信モード設定⑤へ
右PLC 使用可否設定
PLC パワーレベル設定
PLC アドレス設定

局番(アドレス)設定
通信速度設定通信パラメータ設定
通信モード設定⑤Ethernet 通信設定
④へ

右

決定

決定

取消

③へ

決定

決定

取消

RS-485 ﾎﾟｰﾄ 1
ﾀﾝｼﾀﾞｲ ﾋﾀﾞﾘ

－39－

１０－５－１．RS-232C・RS-485 ポート１・RS-485 ポート２通信設定
RS-232C 通信端子、RS-485 通信端子は、各通信端子毎に設定値を記憶しますが、同じ設定項目を持っています。ここでは、RS-232C 通信端子の例を用いて説明します。
項目は、右・左ボタンにて変更します。
決定ボタンを押すと、設定値が点滅し、値の変更が可能になります。
（このとき、設定中ランプが点滅します。）
もう一度決定ボタンを押すと、設定中ランプ及び設定値の点滅が止まり、設定値が保存されます。
設定中でないとき、取消ボタンを押すと、上位の画面に戻ります。

RS-232C
ﾐﾆｼﾞｬｯｸ
決定

取消

232C

ｷｮｸﾊﾞﾝ
S001①局番(アドレス)設定

232C

ﾂｳｼﾝ ｿｸﾄﾞ
9600bps②通信速度設定

左右232C ﾊﾟﾗﾒｰﾀ
7bit Even 1stop③通信パラメータ設定

232C④通信モード設定

ﾂｳｼﾝ ﾓｰﾄﾞ
Mode A①局番(アドレス)設定
通信時の局番(アドレス)を変更する画面です。通常は変更する必要はありませんが、Modbus 通信を行う場合は、変更が必要です。
決定ボタンを押すと、「S」または「0x」の次の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。
通信モード設定値
・Mode A・Mode B1・Mode B2
・Mode C

232C

ｷｮｸﾊﾞﾝ
S001

232C

ｷｮｸﾊﾞﾝ0x01

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

※ CSA-109-D2-R と組み合わせて使用する場合は、「0x10」に設定してください。
②通信速度設定
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

232C

ﾂｳｼﾝ ｿｸﾄﾞ
9600bps

9600bps、19200bps、38400bps が設定可能。

※CSA-109-D2-R と組み合わせて使用する場合は、「9600bps」に設定してください。
Ｔ－５５１７１改訂５－40－

③通信パラメータ設定
通信における、データ長・パリティビット・ストップビットを設定します。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。
設定中は、全ての設定値が点滅します。
右・左ボタンにて設定値の組合わせを選択します。

232C ﾊﾟﾗﾒｰﾀ
7bit Even 1stop

ストップビット：1bit、2bit
パリティビット：None(なし)、Even(偶数)、Odd(奇数)データ長：7bit、8bit を選択※CSA-109-D2-R と組み合わせて使用する場合は、「8bit None 1stop」に設定してください。
④通信モード設定
通信モードは、通常変更する必要はありません。
誤って変更してしまった場合は、「Mode A」に設定してください。
Modbus 通信を行う場合は、「Mode C」に設定します。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

232C「Mode A」：パソコンまたは信号送信装置用通信モード「Mode C」
：Modbus 通信モード「Mode B1」
：特殊仕様モード 1(当社専用)「Mode B2」
：特殊仕様モード 2(当社専用)※ Mode B1 及び Mode B2 は RS-485 端子では設定不可

ﾂｳｼﾝ ﾓｰﾄﾞ
Mode A

１０－５－２．PLC 通信（電力線通信）設定
項目は、右・左ボタンにて変更します。
決定ボタンを押すと、設定値が点滅し、値の変更が可能になります。
（このとき、設定中ランプが点滅します。）
もう一度決定ボタンを押すと、設定中ランプ及び設定値の点滅が止まり、設定値が保存されます。
設定中でないとき、取消ボタンを押すと、上位の画面に戻ります。

PLC
AC100V ﾀﾝｼ
決定

取消

PLC
ｼﾖｳｼﾅｲ

左右①PLC 使用可否設定

PLC ﾊﾟﾜｰ ﾚﾍﾞﾙ50%

②PLC パワーレベル設定

PLC ｱﾄﾞﾚｽ③PLC アドレス設定

0

Ｔ－５５１７１改訂５－41－

①PLC 使用可否設定
PLC（電力線通信）の使用する／使用しないを設定します。
「ｼﾖｳｼﾅｲ」に設定すると、搬送波の出力を停止します。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

PLC
ｼﾖｳｼﾅｲ「ｼﾖｳｼﾅｲ」：使用しない・PLC の搬送波出力を停止します「ｼﾖｳｽﾙ」：使用する・PLC を使用し、デマンドモニターや警報装置に対して、データを出力します②PLC パワーレベル設定
PLC における、搬送波の強さを設定します。
通常、初期値の「50%」から変更する必要はありません。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

PLC ﾊﾟﾜｰ ﾚﾍﾞﾙ50%

10%～100%で設定可能。

③PLC アドレス設定
PLC における、宛先アドレスを設定します。
通常、初期値の「0」から変更する必要はありません。
本設定値に応じて、PLC の出力間隔が変わりますが、特別な場合を除き、変更しないでください。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

PLC ｱﾄﾞﾚｽ0

Ｔ－５５１７１改訂５「０」：出力間隔約５秒「１」：出力間隔約４秒「２」：出力間隔約３秒「３」：出力間隔約２秒－42－１０－５－３．Ethernet 通信設定
項目は、右・左ボタンにて変更します。
決定ボタンを押すと、設定値が点滅し、値の変更が可能になります。
（このとき、設定中ランプが点滅します。）
もう一度決定ボタンを押すと、設定中ランプ及び設定値の点滅が止まり、設定値が保存されます。
設定中でないとき、取消ボタンを押すと、上位の画面に戻ります。

Ethernet
RJ-45 ｼﾞｬｯｸ
決定

左

右

取消

IP ｱﾄﾞﾚｽ
192.168.100.211①IP アドレス設定

ﾏｽｸﾋﾞｯﾄ255.255.255.000②マスクビット設定

ｹﾞｰﾄｳｪｲ
000.000.000.000③ゲートウェイ設定①IP アドレス設定
装置本体の IP アドレスを設定します。
ご利用になるネットワークに合わせて、適切な値を設定ください。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

IP ｱﾄﾞﾚｽ
192.168.100.211

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

②マスクビット設定
ネットワークのマスクビットを設定します。
ご利用になるネットワークに合わせて、適切な値を設定ください。
決定ボタンを押すと、設定値が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ﾏｽｸﾋﾞｯﾄ255.255.255.000

Ｔ－５５１７１改訂５

設定中は、全ての桁が点滅します。
右・左ボタンにて適切な値を選択します。

－43－

③ゲートウェイ設定
ゲートウェイとなる機器の IP アドレスを設定します。
ご利用になるネットワークに合わせて、適切な値を設定ください。
PC とクロス結線の LAN ケーブルで直結される場合など、ゲートウェイを特に設定しない場合は、「000.000.000.000」に設定してください。
決定ボタンを押すと、左端の桁が点滅します。
右・左ボタンにて、値を変更します。
設定中のとき、決定ボタンを押すと、設定中の桁が移動します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、設定を中止します。

ｹﾞｰﾄｳｪｲ
000.000.000.000

Ｔ－５５１７１改訂５

一桁ずつ設定します。
最後の桁で決定ボタンを押すと、値確定。

－44－

１０－６．テストモード
テストモードを使用すると、制御出力の ON／OFF テスト、装置本体のランプテスト、PLC の出力テストを行うことができます。
※ テストモード終了後は、取消ボタンを押して、必ず時計表示画面に戻してください。
右・左ボタンにて項目を変更します。
決定ボタンを押すと、各項目のテスト動作を実行します。
取消ボタンを押すと、上位の画面に戻ります。

ﾃｽﾄ ﾓｰﾄﾞ
決定

左

右

取消

ｾｲｷﾞｮｼｭﾂﾘｮｸ ﾃｽﾄ
OFF OFF OFF OFF①制御出力テスト

ﾗﾝﾌﾟ ﾃｽﾄ
00 0000②ランプテスト

0000

PLC ﾃｽﾄ 9.0kHz
Out:OFF
Sig:0③PLC テスト①制御出力テスト
制御出力テストでは、制御出力端子を強制的に ON／OFF 制御します。
連動する機器の入力確認などにお使い頂けますが、制御出力テスト中は、デマンド監視による警報出力ができなくなりますので、ご注意ください。
決定ボタンを押すと、左端の「OFF」表示が点滅し、設定中ランプが点滅します。
右・左ボタンにて、「ON」「OFF」を変更します。
このとき、決定ボタンを押すと、次の制御出力の ON／OFF 表示が点滅します。
一番右の桁が点滅しているときに、決定ボタンを押すと、設定値を確定し登録します。
取消ボタンを押すと、制御出力テストを終了します。

ｾｲｷﾞｮｼｭﾂﾘｮｸ ﾃｽﾄ
OFF OFF OFF OFF

テスト中、該当の項目が点滅します。
右・左ボタンで状態を変更します。
変更した状態は、端子の状態に直ちに反映されます。

制御出力４
制御出力３
制御出力２
制御出力１

Ｔ－５５１７１改訂５－45－

②ランプテスト
ランプテストでは、装置前面パネルの電源ランプを除くランプを任意に ON／OFF することができます。
通常の使用において、ランプテストを行う必要はありません。
決定ボタンを押すと、左端の「0」表示にカーソルが点滅します。
右・左ボタンにて、「0」「1」を変更します。
「0」がランプ消灯、「1」がランプ点灯を意味し、対応するランプを制御します。
決定ボタンを押すと、カーソルを 1 つ隣へ移動します。
取消ボタンを押すと、ランプテストを終了します。

ﾗﾝﾌﾟ ﾃｽﾄ
00 00000000

テスト中、該当の項目にカーソルを表示。
右・左ボタンで状態を変更します。
変更した状態は、ランプの状態に直ちに反映されます。

電界強度 圏外・■・■■・■■■（LTE 有りの場合のみ制御可能）
制御出力１～４（出力端子とは連動しません）
設定中・異常③PLC テスト
PLC テストでは、搬送波を強制的に出力します。
通常の使用において、PLC テストを行う必要はありません。
決定ボタンを押すと、PLC テストの ON／OFF を切り替えます。
PLC テストが ON のとき、搬送波出力を ON にするとともに、設定中ランプが点滅します。
右・左ボタンにて、信号状態「0」「1」を変更します。
搬送波出力 ON のとき、取消ボタンを押すと、PLC テストを終了します。

PLC ﾃｽﾄ 9.0kHz
Out:OFF
Sig:0

搬送周波数
（本体取り外し可能フタ内のスライドスイッチの設定状態を表示します)信号状態：０または１を右・左ボタンで切り替え
出力状態：ON のとき、PLC テストモードとして強制出力中を意味します。

Ｔ－５５１７１改訂５－46－

１０－７．USB メモリの操作（計測データ：出力、設定値：入出力）
USB メモリへ計測データを出力したり、設定値を入出力する場合に、本機能を使用します。
決定ボタンを押すと、データ出力メニューを表示します。
取消ボタンを押すと、上位の画面に戻ります。

USB ｿｳｻ
決定取消
左右ﾃﾞｰﾀ ｼｭﾂﾘｮｸ

①データ出力（計測データのファイル出力）

ﾈﾝﾎﾟｳ ｼｭﾂﾘｮｸ

②年報出力（年報帳票のファイル出力）

ｾｯﾃｲﾁ ﾆｭｳｼｭﾂﾘｮｸ

③設定値入出力（設定値ファイルの入出力）

ﾊﾞｯｸｱｯﾌﾟ/ﾌｸｹﾞﾝ④バックアップ／復元（データ＋設定値の入出力）

Ｔ－５５１７１改訂５－47－

①データ出力（計測データのファイル出力）
決定ボタンを押すと、ファイルタイプ選択画面を表示しますので、右・左ボタンにて、「CSV」
または「XLS」を選択し、決定ボタンを押します。
「XLS」を選択の場合、USB メモリに予めテンプレートファイルを入れておく必要があります。
データは 1 ヶ月分出力しますので、開始年月日を設定します。
なお、「日」は 1～28 日で設定してください。
「日」を設定後に決定ボタンを押すと、出力開始します。

ﾃﾞｰﾀ ｼｭﾂﾘｮｸ
決定

取消

ﾌｧｲﾙ ﾀｲﾌﾟ
CSV
決定
取消

ｼｭﾂﾘｮｸ ｶｲｼﾋﾞ
2013/12/01

右・左ボタンでファイルタイプを選択「CSV」：CSV フォーマット
（テキスト形式、カンマ区切り）「XLS」：Excel フォーマット
（Microsoft 社の Excel で読み込めるフォーマット）
出力開始日を設定（日は 1～28 日で設定します）
右・左ボタンで値変更
決定ボタンで次の項目へ移動「日」設定後に決定

ﾃﾞｰﾀ ｼｭﾂﾘｮｸ ﾁｭｳ
ﾒﾓﾘ > USB
0%
Out:OFF
Sig:0
出力正常完了時

出力失敗時

次ページ、出力失敗時のメッセージと対処方法参照

ｼｭﾂﾘｮｸ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ
Out:OFF Sig:0
決定
データ出力画面に戻ります

Ｔ－５５１７１改訂５－48－出力失敗時のメッセージと対処方法「USB ﾒﾓﾘ ｶﾞ ｱﾘﾏｾﾝ」→ USB メモリを接続してください。
「ﾃﾝﾌﾟﾚｰﾄ ｶﾞ ｱﾘﾏｾﾝ」→ テンプレートファイルを USB メモリに入れてください。
「ﾌｧｲﾙｺﾋﾟｰｴﾗｰ」→ USB メモリに空き容量がないか、書き込み禁止になっています。
USB メモリの空き容量と、書き込み禁止になっていないか確認してください。
「ﾃﾝﾌﾟﾚｰﾄ ｶﾞ ｲｼﾞｮｳ」
・「ﾌｧｲﾙ ｼｭﾂﾘｮｸ ｴﾗｰ」
→ テンプレートファイルが破損しています。
（マクロプログラムを含んでいる場合や、ファイルサイズが異常に大きい場合など）
新規にテンプレートファイルを入れ直し、もう一度試みてください。

※ ファイルに出力される電力量データについて
１時間毎の電力量データは、下記計算式にて求めます。
（該当時の 0 分～30 分までのデマンド電力 ＋ 該当時 30 分～次の 0 分までのデマンド電力）／ ２
計算結果は小数点第二位を四捨五入してから出力します。
CSV フォーマットで出力する場合、電力量の計算は、出力時に装置内で行われます。
Excel フォーマットで出力する場合、電力量の計算はテンプレートファイルのシート内に設定した計算
式により行われます。予めご留意ください。

Ｔ－５５１７１改訂５－49－

②年報出力（年報帳票のファイル出力）
決定ボタンを押すと、出力年月選択画面を表示しますので、右・左ボタンにて、年報を出力する
年月をを選択し、決定ボタンを押すと、出力開始します。

ﾈﾝﾎﾟｳ ｼｭﾂﾘｮｸ
決定

取消

ｼｭﾂﾘｮｸ ｶｲｼﾈﾝｹﾞﾂ
2013/10出力開始年月を設定
右・左ボタンで値変更
決定ボタンで次の項目へ移動

設定後に決定取消

ﾃﾞｰﾀ ｼｭﾂﾘｮｸ ﾁｭｳ
ﾒﾓﾘ > USB
0%
Out:OFF
Sig:0
出力正常完了時

出力失敗時

出力失敗時のメッセージと対処方法参照

ｼｭﾂﾘｮｸ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ
Out:OFF Sig:0
決定
データ出力画面に戻ります
出力失敗時のメッセージと対処方法「USB ﾒﾓﾘ ｶﾞ ｱﾘﾏｾﾝ」→ USB メモリを接続してください。
「ﾃﾝﾌﾟﾚｰﾄ ｶﾞ ｱﾘﾏｾﾝ」→ テンプレートファイルを USB メモリに入れてください。
「ﾌｧｲﾙｺﾋﾟｰｴﾗｰ」→ USB メモリに空き容量がないか、書き込み禁止になっています。
USB メモリの空き容量と、書き込み禁止になっていないか確認してください。
「ﾃﾝﾌﾟﾚｰﾄ ｶﾞ ｲｼﾞｮｳ」
・「ﾌｧｲﾙ ｼｭﾂﾘｮｸ ｴﾗｰ」
→ テンプレートファイルが破損しています。
（マクロプログラムを含んでいる場合や、ファイルサイズが異常に大きい場合など）
新規にテンプレートファイルを入れ直し、もう一度試みてください。

Ｔ－５５１７１改訂５－50－

③設定値入出力（設定値ファイルの入出力）
決定ボタンを押すと、設定値を USB メモリから読み込むのか、設定値を USB メモリへ出力するのかを選択する画面を表示しますので、右・左ボタンにて選択し、決定ボタンを押します。

ｾｯﾃｲﾁ ﾆｭｳｼｭﾂﾘｮｸ
決定取消

ｿｳｻ ｾﾝﾀｸ
ﾒﾓﾘ USB
決定取消

右・左ボタンで操作を選択「ﾒﾓﾘ USB」：設定値の出力装置の設定値内容を USB メモリへ出力「USB ﾒﾓﾘ」：設定値の入力
USB メモリ内の設定値ファイルの内容で装置を設定「ﾒﾓﾘ USB」：設定値の出力「USB ﾒﾓﾘ」：設定値の入力

ｾｯﾃｲﾁ ｼｭﾂﾘｮｸ
ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

ｾｯﾃｲﾁ ﾆｭｳﾘｮｸ
ｶｲｼ ｼﾏｽｶ?
ｲｲｴ「ﾊｲ」に変更して決定

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します

ﾎﾝﾄｳﾆ ｶｲｼ ｼﾏｽｶ?
ｲｲｴ「ﾊｲ」に変更して決定
入出力の状態に応じて表示内容が変わります。

ｾｯﾃｲﾁ ｼｭﾂﾘｮｸ ﾁｭｳ
ﾒﾓﾘ> USB
XXX%

100%になると、次の画面に自動的に切り替わります

失敗時

ｼｭﾂﾘｮｸ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ

下記、失敗時のメッセージと対処方法参照

決定
設定値入出力画面に戻ります
失敗時のメッセージと対処方法「USB ﾒﾓﾘ ｶﾞ ｱﾘﾏｾﾝ」→ USB メモリを接続してください。
「ﾌｧｲﾙ ｶﾞ ｱﾘﾏｾﾝ」→ 設定ファイルを USB メモリに入れてください。
「ﾌｧｲﾙ ｶﾞ ｲｼﾞｮｳ」
・「ﾌｧｲﾙ ｼｭﾂﾘｮｸ ｴﾗｰ」・「ﾃﾞｰﾀ ｴﾗｰ: XXXX」→ 設定ファイルが破損しています。
設定値出力の場合は、USB メモリを初期化した後で、もう一度試みてください。
設定値入力場合は、新規に設定ファイルを入れ直し、もう一度試みてください。
※ 設定ファイルのフォーマットについて
設定ファイルは、専用フォーマットとなっております。
弊社製の設定ソフト以外では編集しないでください。
Ｔ－５５１７１改訂５－51－

④バックアップ／復元（データ＋設定値の入出力）
決定ボタンを押すと、バックアップしたデータを USB メモリへ出力するのか、USB メモリから入力するのかを選択する画面を表示しますので、右・左ボタンにて選択し、決定ボタンを押します。

ﾊﾞｯｸｱｯﾌﾟ/ﾌｸｹﾞﾝ
決定取消

ｿｳｻ ｾﾝﾀｸ
ﾒﾓﾘ→USB
決定取消

右・左ボタンで操作を選択「ﾒﾓﾘ→USB」：バックアップデータの出力
バックアップデータを USB メモリへ出力「USB→ﾒﾓﾘ」：バックアップデータの入力
USB メモリ内のバックアップデータファイルの内容
で装置状態を復元※ バックアップデータの出力先、入力元は、次ページ
バックアップデータの入出力場所参照「ﾒﾓﾘ→USB」：データのバックアップ「USB→ﾒﾓﾘ」：バックアップデータの復元

ﾃﾞｰﾀ ﾊﾞｯｸｱｯﾌﾟ
ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

ﾃﾞｰﾀ ﾌｸｹﾞﾝ
ｶｲｼ ｼﾏｽｶ?

「ﾊｲ」に変更して決定

ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します

ﾎﾝﾄｳﾆ ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

次ページ、失敗時のメッセージと対処方法参照「ﾊｲ」に変更して決定「ﾒﾓﾘ→USB」：データのバックアップ

失敗時「USB→ﾒﾓﾘ」：バックアップデータの復元

ﾃﾞｰﾀ ﾊﾞｯｸｱｯﾌﾟﾁｭｳ
ﾒﾓﾘ> USB
XXX%

ﾃﾞｰﾀ ﾌｸｹﾞﾝﾁｭｳ
USB> ﾒﾓﾘ
XXX%

100%になると、次の画面に自動的に切り替わります

ﾊﾞｯｸｱｯﾌﾟ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ

ﾌｸｹﾞﾝ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ

決定

決定バックアップ／復元画面に戻ります

Ｔ－５５１７１改訂５装置が再起動します。

－52－

バックアップデータの入出力場所
バックアップデータは USB メモリのルートおよび装置のシリアル番号を使用したフォルダ内の２箇所に保存します。
ファイル名は「FERAM.bin」となります。
例） USB メモリのドライブが「C」、装置のシリアル番号が「01-02-03-04-05-06」の場合、ファイル
保存先は下記の２箇所となります。
① C:¥② C:¥ID040506¥

なお、復元の場合には装置のシリアル番号を使用したフォルダに存在しているファイルを優先して使用します。

失敗時のメッセージと対処方法「USB ﾒﾓﾘ ｶﾞ ｱﾘﾏｾﾝ」→ USB メモリを接続してください。
「ﾌｧｲﾙ ｶﾞ ｱﾘﾏｾﾝ」→ バックアップデータファイルを USB メモリに入れてください。
「ﾌｧｲﾙ ｶﾞ ｲｼﾞｮｳ」
・「ﾌｧｲﾙ ｼｭﾂﾘｮｸ ｴﾗｰ」・「ﾃﾞｰﾀ ｴﾗｰ: XXXX」→ バックアップデータファイルが破損しています。
バックアップの場合は、USB メモリを初期化した後で、もう一度試みてください。
復元の場合は、新規にファイルを入れ直し、もう一度試みてください。
※ バックアップデータファイルのフォーマットについて
バックアップデータファイルは、専用フォーマットとなっております。
内容を改変しないでください。

Ｔ－５５１７１改訂５－53－

１１．特殊操作モード
１１－１．特殊操作モード画面一覧
設定メニュー画面表示中に、右・左ボタンを長押しすると、特殊操作モードになります。

12:34:56 1234kW
ﾖｿｸ 1234kW

時計表示

決定
取消

ｼｽﾃﾑ ｾｯﾃｲ「ｼｽﾃﾑ ｾｯﾃｲ」などの設定メニュー画面
右・左長押しﾄｸｼｭ ｿｳｻ ﾓｰﾄﾞ

特殊操作モードメニュー画面

決定取消①ソフトウェアアップデート
左ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ

決定

アップデート確認画面へ②電力量設定ﾃﾞﾝﾘｮｸﾘｮｳ ｾｯﾃｲ
12345678kWh

決定

電力量編集画面へ③ALL リセット

ALL ﾘｾｯﾄ決定

ALL リセット確認画面へ④Web サーバ初期化

Webｻｰﾊﾞ ｼｮｷｶ

決定Web サーバ初期化確認画面へ⑤装置再起動右ｿｳﾁ ｻｲｷﾄﾞｳ

Ｔ－５５１７１改訂５

決定装置再起動確認画面へ－54－

１１－２．ソフトウェアアップデート（１）はじめに※ ソフトウェアの更新中、データの通信は行いません。
※ ソフトウェアの更新中（特に、画面右上に「USB」を表示中）は、USB メモリを抜いたり、電源を OFF にしないでください。
最悪の場合、起動できなくなります。この場合、弊社営業までお問い合せください。
（弊社工場での修理対応となります。）※ USB メモリに保存したデータには影響しません。
（USB メモリのデータは削除しません）（２）準備
USB メモリに弊社提供の更新ファイルを入れ、デマンド監視装置に接続してください。
※ 更新ファイルは、フォルダに入れず、ドライブの直下に入れてください。

（３）操作

12:34:56 1234kW
ﾖｿｸ 1234kW
決定ｼｽﾃﾑ ｾｯﾃｲ
右・左長押し時計表示

ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ

ソフトウェアアップデート画面

決定右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します

ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ
ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

ﾄｸｼｭ ｿｳｻ ﾓｰﾄﾞ「ﾊｲ」に変更して決定
決定右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します

ﾎﾝﾄｳﾆ ｶｲｼ ｼﾏｽｶ?
ｲｲｴ「ﾊｲ」に変更して決定

ｱｯﾌﾟﾃﾞｰﾄ ﾁｭｳ
USB > FLASH XXX%
ｲｲｴ
正常時

100%になると、次の画面に自動的に切り替わります

失敗時

ｱｯﾌﾟﾃﾞｰﾄ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ
決定再起動しますここまでの操作で、アップデート完了です

Ｔ－５５１７１改訂５

－55－

次ページ
アップデート失敗時のメッセージ
と対処方法
参照

アップデート失敗時のメッセージと対処方法「USB ﾒﾓﾘ ｶﾞ ｱﾘﾏｾﾝ」→ USB メモリを接続してください「ﾌｧｲﾙ ｶﾞ ﾐﾂｶﾘﾏｾﾝ」→ 更新ファイルを USB メモリに入れてください「ﾌｧｲﾙ ｶﾞ ｲｼﾞｮｳﾃﾞｽ」→ 更新ファイルの内容が破損しています。
USB メモリをフォーマットし、更新ファイルを入れ直し、再度試みてください「ｱｯﾌﾟﾃﾞｰﾄ ｴﾗｰ」
→ 何らかの要因により、アップデートが失敗しました。
このとき、装置の電源は絶対に OFF にしないでください。
決定ボタンを押すと、再度アップデートを試みます。

１１－３．電力量表示の値設定（１）はじめに通常モードの電力量表示は、値を設定することができます。
電力量計の値に合わせることで、電力量計との値比較にご利用いただけます。

（２）操作

12:34:56 1234kW
ﾖｿｸ 1234kW
決定ｼｽﾃﾑ ｾｯﾃｲ
右・左長押し時計表示

ﾃﾞﾝﾘｮｸﾘｮｳ ｾｯﾃｲ
12345678kWh

電力量設定画面決定

ﾃﾞﾝﾘｮｸﾘｮｳ ｾｯﾃｲ
12345678kWh

ﾄｸｼｭ ｿｳｻ ﾓｰﾄﾞ
決定

ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ

右Ｔ－５５１７１改訂５

一桁ずつ設定します。
右・左ボタンにて、値を変更します。
決定ボタンを押すと、設定中の桁が移動します。
最後の桁で決定ボタンを押すと、値確定します。
取消ボタンを押すと、設定を中止します。
設定値確定時、小数点以下の値はゼロクリアされます。

－56－

１１－４．オールリセット（初期化）（１）はじめに
ここで説明する初期化操作を行うと、装置本体の記録データをクリアするとともに、設定値も初期化します。

（２）操作

12:34:56 1234kW
ﾖｿｸ 1234kW

時計表示

決定

ALL ﾘｾｯﾄALL リセット画面

ｼｽﾃﾑ ｾｯﾃｲ
決定
右・左長押しﾄｸｼｭ ｿｳｻ ﾓｰﾄﾞ

ALL ﾘｾｯﾄｶｲｼ ｼﾏｽｶ?

ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します「ﾊｲ」に変更して決定
決定ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ

ﾎﾝﾄｳﾆ ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します「ﾊｲ」に変更して決定
右ALL ﾘｾｯﾄ ｼﾏｼﾀ
ｹｯﾃｲ ｦ ｵｼﾃ ｸﾀﾞｻｲ
ﾃﾞﾝﾘｮｸﾘｮｳ ｾｯﾃｲ
12345678kWh
右Ｔ－５５１７１改訂５

決定
ALL リセット画面に戻ります。
取消ボタンを 2 回押すと、時計表示に戻ります。

－57－

１１－５．Web サーバ初期化（１）はじめに
ここで説明する初期化操作を行うと、Web サーバ機能用のデータが、工場出荷状態に戻ります。
本装置の Web サーバデータをカスタマイズした後、元へ戻す必要がある場合にご使用ください。
初期化動作中は、Web サーバ機能がご使用いただけません。
Web サーバデータカスタマイズ時に変更したデータ及び追加したファイルは、本初期化操作にてクリアされます。

（２）操作

12:34:56 1234kW
ﾖｿｸ 1234kW

時計表示

決定

Webｻｰﾊﾞ ｼｮｷｶ

Web サーバ初期化画面

ｼｽﾃﾑ ｾｯﾃｲ
決定
右・左長押しﾄｸｼｭ ｿｳｻ ﾓｰﾄﾞ

Webｻｰﾊﾞ ｼｮｷｶ
ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します「ﾊｲ」に変更して決定
決定ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ

ﾎﾝﾄｳﾆ ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します「ﾊｲ」に変更して決定
左ｿｳﾁ ｻｲｷﾄﾞｳ

左Webｻｰﾊﾞ ｼｮｷｶ ﾁｭｳ
RAM > FLASH XXX%
ｲｲｴ
正常時

100%になると、次の画面に自動的に切り替わります

ｼｮｷｶ ｶﾝﾘｮｳ
ｹｯﾃｲ ｦ ｵｼﾃｸﾀﾞｻｲ
決定Web サーバ初期化画面に戻ります。
取消ボタンを 2 回押すと、時計表示に戻ります。

Ｔ－５５１７１改訂５－58－

１１－６．装置再起動（１）はじめに
ここで説明する操作を行うと、装置を強制的に再起動します。
通信や USB へのファイル入出力が正常に行えない場合において、電源の再投入ができない時にご使用ください。

（２）操作

12:34:56 1234kW
ﾖｿｸ 1234kW

時計表示

決定

ｼｽﾃﾑ ｾｯﾃｲ
右・左長押しﾄｸｼｭ ｿｳｻ ﾓｰﾄﾞ
決定

ｿﾌﾄｳｪｱ ｱｯﾌﾟﾃﾞｰﾄ
左ｿｳﾁ ｻｲｷﾄﾞｳ

装置再起動画面決定

ｿｳﾁ ｻｲｷﾄﾞｳ
ｶｲｼ ｼﾏｽｶ?

ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します「ﾊｲ」に変更して決定

ﾎﾝﾄｳﾆ ｶｲｼ ｼﾏｽｶ?
ｲｲｴ

右・左ボタンで、「ﾊｲ」に変更し、決定ボタンを押します「ﾊｲ」に変更して決定装置が再起動します。

Ｔ－５５１７１改訂５－59－

１２．Web サーバ機能
１２－１．はじめに本装置は、Web サーバ機能を搭載しています。
ハブやアクセスポイントを介してパソコンなどの Web ブラウザから計測データの確認や設定を行うことができます。
※ 対応するブラウザは、Google Chrome です。
これら以外のブラウザでもご利用になれる場合がありますが、データを正常に表示できない可能性があります。
※ 本装置への Web 接続台数は、３台までです。
または、ブラウザのタブ３枚、或いはウインドウ３枚までとしてください。
上記を超えて接続した場合、画面のデータ更新が遅くなる場合があります。
※ メニュー画面と設定画面を除き、画面内のデータは約 10 秒で自動更新します。
但し、端末のスペックや動作状況により、時間がかかる場合があります。
※ 本書に示す表示画面内容は、基本的な項目のみです。
今後のバージョンアップにより、デザインや表示項目が変わる場合があります。
※ 警報状態を表示する画面において、複数の警報が発生している場合、下記の優先度で表示します。
優先度大 機器異常 ＞ 限界警報 ＞ 警戒警報 ＞ 注意警報 優先度小なお、警報音は鳴りません。

１２－２．準備
本装置に、IPv４形式の固定の IP アドレスを割り当ててください。
設定は、本装置の通信設定で行ってください。
※ 本装置は、「ping」に対する応答を返します。通信確認にご利用ください。

１２－３．Web アクセスする
ここでは、デマンド監視装置の IP アドレスとして「192.168.55.236」を設定し、Google Chromeで閲覧した場合の例を示します。
Web ブラウザを開き、URL として「http://192.168.55.236」を入力し、Enter キーを押すと、メニュー画面を表示します。

※ 以降のページで紹介する画面例は、URL 内の IP アドレスが上記 IP アドレスと異なっております。実際は装置の IP アドレスを表示しますので、予めご留意ください。

Ｔ－５５１７１改訂５－60－

１２－４．Web 画面詳細
（１）メニュー画面

30 分デマンドグラフを表示します
過去 24 時間のデマンド電力や電力量をグラフ表示します過去 30 日間の電力量をグラフ表示します
警報の履歴画面を表示します
帳票出力画面を表示します。

（２）現在デマンド画面
現在デマンド画面は、現在の時限における 30 分デマンドの推移を表示する画面と、2 分毎の平均電力を表示する画面と、制御状態を表示する画面に分かれています。
①現在の電力状況画面
現在の時限における 30 分デマンドの推移と、警報の発生状態をグラフ表示します。
「目標電力」は、デマンド監視装置に設定した「限界電力設定値」の値を表示します。
デマンド監視装置に設定した「注意電力設定値」の値を警報発生のライン（青い線）として表示します。
クリックすると、各画面に切り替え

Ｔ－５５１７１改訂５－61－

②2 分毎の平均電力画面
現在の時限における 30 分間分の、2 分毎の平均電力をグラフ表示します。
2 分毎の平均電力を棒グラフとして表示します。
クリックすると、各画面に切り替え③制御状態画面
現在の時限における接点制御出力の推移をグラフ表示します。
クリックすると、各画面に切り替え※ 出力が ON の状態で本装置が停電し同時限内に復電した場合、停電の影響によりグラフ上では停電時の位置の瞬時電力が 0kW、出力が OFF のように表示されます。

Ｔ－５５１７１改訂５－62－

（３）時間別グラフ画面
時間別グラフ画面は、過去 24 時間のデマンド電力を表示する画面と、過去 24 時間の電力量を表示する画面に分かれています。
①1 日のデマンド電力画面
過去 24 時間のデマンド電力の推移をグラフ表示します。
デマンド監視装置に設定した「限界電力設定値」を目標ラインとして表示します。
クリックすると、電力量表示に切り替え②1 日の電力使用量画面
過去 24 時間における、1 時間毎の電力量推移をグラフ表示します。
クリックすると、デマンド電力表示に切り替え

Ｔ－５５１７１改訂５－63－

（４）1 ヶ月の電力使用量画面
過去 30 日間における、1 日毎の電力量推移をグラフ表示します。
最大値及び合計値は、デマンド監視装置が 30 日以上動作している場合に、表示します。

（５）警報履歴画面
デマンド警報や機器異常警報の履歴を表示します。
最初に、読み出し件数を指定します。
「読出し」ボタンを押すと、指定件数を読み出します。
50 件／500 件／5000 件を選択クリックすると、読み出し開始

50 件または 500 件を指定したとき、デマンド監視装置がその件以上記憶していた場合は、件数には指定件数を表示します。

Ｔ－５５１７１改訂５－64－

（６）帳票出力画面
指定月の月報、指定日の日報、指定年の年報を出力します。
帳票の種類と開始日を設定後、「帳票表示」をクリックすると、画面に帳票を表示します。
【月報／日報の場合】
月報／日報／年報を選択

クリックすると、カレンダーを表示しますので、月報の開始日／日報の出力日を指定します。
帳票の種類と開始日を設定後、クリックすると、帳票出力開始します。

【年報の場合】
月報／日報／年報を選択

年報の開始月を指定します。

帳票の種類と開始月を設定後、クリックすると、帳票出力開始します。

Ｔ－５５１７１改訂５－65－

① 月報出力例※ 合成変成比設定が 9999 以下の時、電力及び電力量データは小数点第一位まで表示します。
合成変成比設定が 10000 以上の時、電力及び電力量データは整数で表示します。
このため、時間別グラフ画面で表示している値と一致しない場合があります。

Ｔ－５５１７１改訂５－66－

② 日報出力例
限界電力設定値として設定した値が、グラフ中に目標ラインとして描画されます。

※ 合成変成比設定が 9999 以下の時、電力及び電力量データは小数点第一位まで表示します。
合成変成比設定が 10000 以上の時、電力及び電力量データは整数で表示します。
このため、時間別グラフ画面で表示している値と一致しない場合があります。

Ｔ－５５１７１改訂５－67－

③ 年報出力例※ 合成変成比設定が 9999 以下の時、電力及び電力量データは小数点第一位まで表示します。
合成変成比設定が 10000 以上の時、電力及び電力量データは整数で表示します。

Ｔ－５５１７１改訂５－68－

１３．CSV フォーマット詳細
１３－１．ファイル名
出力時に設定した出力開始日がファイル名となります。
例：出力開始日を「2013/12/01」とした場合、ファイル名は「20131201.csv」となります。
１３－２．フォーマット
（１）具体例①

2013,12,1,②

kW Data,"YYYY/MM/DD", 00:00, 00:30, 01:00, 01:30,"2013/12/01", 18.7, 18.6, 19.1, 23.0,"2013/12/02", 17.8, 18.2, 18.4, 22.7,"2013/12/03", 16.2, 16.1, 15.9, 20.3,, 22:30, 23:00, 23:30,, 18.0, 21.0, 17.2,, 27.0, 21.0, 17.5,, 22.5, 19.4, 16.3,"2013/12/29","2013/12/30","2013/12/31",

,
,
,

③

④

18.3,
30.0,
27.5,

15.3,
24.9,
27.8,

15.0,
29.5,
28.2,

19.3,
29.4,
28.0,

27.0,
28.4,
20.8,

kWh Data,"YYYY/MM/DD", 00:00, 01:00, 02:00,"2013/12/01", 18.7, 21.1, 21.9,"2013/12/02", 18.0, 20.5, 22.4,"2013/12/03", 16.2, 18.1, 21.0,, 22:00, 23:00,, 18.1, 19.1,, 29.3, 19.3,, 24.4, 17.9,"2013/12/29","2013/12/30","2013/12/31",

,
,
,

16.8,
27.5,
27.7,

17.2,
29.5,
28.1,

18.5,
29.1,
27.1,

27.3,
29.0,
20.8,

24.8,
28.9,
20.1,

22.5,
27.1,
23.1,

23.7,
28.0,
21.6,

Max and Total Data,"YYYY/MM/DD", kW(Max), kWh(Total),"2013/12/01",
24.3,
445.5,"2013/12/02", 231.8,
2569.6,"2013/12/03", 215.2,
2424.7,"2013/12/29","2013/12/30","2013/12/31",

43.0,
33.2,
28.9,

601.7,
633.2,
549.6,※ 合成変成比設定が 9999 以下の時、電力及び電力量データは小数点第一位まで表示します。
合成変成比設定が 10000 以上の時、電力及び電力量データは整数で表示します。

Ｔ－５５１７１改訂５－69－

（２）各データの詳細①出力開始日項目名②デマンド電力
項目名

データ内容
出力開始日（年,月,日）

00:00
00:30
01:00
01:30

データ内容
記録日（年/月/日）
出力開始日から 1 ヶ月分を出力します。
例：出力開始日を「2013/11/15」とした場合、「2013/11/15」～「2013/12/14」を出力します。
00:00～00:30 のデマンド電力
00:30～01:00 のデマンド電力
01:00～01:30 のデマンド電力
01:30～02:00 のデマンド電力

22:30
23:00
23:30

22:30～23:00 のデマンド電力
23:00～23:30 のデマンド電力
23:30～00:00 のデマンド電力

項目名"YYYY/MM/DD"
00:00
01:00
02:00

データ内容
②の"YYYY/MM/DD"と同様
00:00～01:00 の電力量
01:00～02:00 の電力量
02:00～03:00 の電力量

22:00
23:00

22:00～23:00 の電力量
23:00～00:00 の電力量

"YYYY/MM/DD"③電力量④日毎の最大デマンド値と累積電力量
項目名
データ内容
②の"YYYY/MM/DD"と同様"YYYY/MM/DD"
記録日の最大デマンド値
kW(Max)記録日の累積電力量
kWh(Total)

Ｔ－５５１７１改訂５－70－

１４．外形寸法図（１）装置本体

Ｔ－５５１７１改訂５－71－

（２）デマンド警報装置（デマンド警報 2 点）

130
32

332
2

116
6

3.5φ穴

3.5
3.5

信号送信装置
デマンド警報装置
電源119900機器異常
限界 機器異常
余裕注意 注意 限界

ﾌﾞｻﾞｰ停止

記名板

通信エラー

ＴＡ ＫＥ ＭＯ ＴＯ
ＴＡ Ｋ Ｅ ＭＯ Ｔ Ｏ
1

11 12

3

13

14

CO

N
1 2 3 4 5 6 7 8１ 9 1O0

１

1 2O F3 F4 5 6

音量

1 2 3 4 5 6

モード

AC100V
電源 2

２
CI
4 ﾊﾞﾝﾄﾞ

レ
ベ
ル

モード

+２ - S G

レベ
電源 ル
AC100Vﾊﾞﾝﾄﾞ
RS-485

+

-

ブザー

SG

端子カバー
電 源ｺｰﾄﾞ 0.75m㎡ 電 源ｺｰﾄﾞ 0.75m㎡
端子カバー
約３ｍ付属
取り外し可能蓋取付
約３ｍ付属
内 部 に 端取
子り
台外
，し
設可
定能
ス蓋
イ取
ッ付
チ取付

3.5
40

内部に端子台，
設定スイッチ取付
赤
＋

白
－

黒

３芯ｷｬﾌﾟﾀｲﾔｹｰﾌﾞﾙ
約0.5ｍ

入線口

SG

端 子ｶﾊﾞｰ 上 面 図
警

報

状

態

余

条

件

予想デマンドが目標デマンド
以下である場合

注意

予想デマンドが目標デマンド超過でかつ契約電力以下である場合

限界予想デマンドが目標デマンド超過でかつ契約電力超過である場合

記名板 ケース右側面貼付
製品名
受信装置
形番
ＴＤＤ３ＺＢ－Ｒ
ＡＣ１００Ｖ ５０／６０Ｈｚ
消費電力 ３Ｗ
信号点数 ３点
製造番号 ＹＹＭＭＳＳＳＳ
製造年
２０＊＊年
ＨＡＫＡＲＵ ＰＬＵＳ

※ 製造番号は YYMMSSSS の構成
YY:西暦年下 2 桁、MM:月、SSSS:連番

Ｔ－５５１７１改訂５

裕

板状形圧着端子

－72－

ランプ

ブザー

緑点灯

無

黄点灯

間欠音
（ピッピッピッ）

赤点灯

連続音
（ピー）

（３）デマンド警報装置（デマンド警報 3 点）

130
32

332
2

116
6

3.5φ穴

3.5
3.5

信号送信装置
デマンド警報装置
電源119900

機器異常
限界
余裕注意 注意
注意 限界
警戒 機器異常限界

ﾌﾞｻﾞｰ停止

記名板

通信エラー

ＴＡ ＫＥ ＭＯ ＴＯ
ＴＡ Ｋ Ｅ ＭＯ Ｔ Ｏ
1

11 12

3

13

14

CO

N
1 2 3 4 5 6 7 8１ 9 1O0

１

1 2O F3 F4 5 6

音量

1 2 3 4 5 6

モード

AC100V
電源 2

２
CI
4 ﾊﾞﾝﾄﾞ

レ
ベ
ル

モード

+２ - S G

レベ
電源 ル
AC100Vﾊﾞﾝﾄﾞ
RS-485

+

-

ブザー

SG

端子カバー
電 源ｺｰﾄﾞ 0.75m㎡ 電 源ｺｰﾄﾞ 0.75m㎡
端子カバー
約３ｍ付属
取り外し可能蓋取付
約３ｍ付属
内 部 に 端取
子り
台外
，し
設可
定能
ス蓋
イ取
ッ付
チ取付

3.5
40

内部に端子台，
設定スイッチ取付
赤
＋

白
－

黒

３芯ｷｬﾌﾟﾀｲﾔｹｰﾌﾞﾙ
約0.5ｍ

入線口

SG

端 子ｶﾊﾞｰ 上 面 図
警

報

状

態

余

条

件

予想デマンドが目標デマンド
以下である場合

注意

予想デマンドが目標デマンド超過でかつ契約電力以下である場合

限界予想デマンドが目標デマンド超過でかつ契約電力超過である場合

記名板 ケース右側面貼付
製品名
受信装置
形番
ＴＤＤ３ＺＢ－Ｒ－Ｘ１
ＡＣ１００Ｖ ５０／６０Ｈｚ
消費電力 ３Ｗ
信号点数 ３点
製造番号 ＹＹＭＭＳＳＳＳ
製造年
２０＊＊年
ＨＡＫＡＲＵ ＰＬＵＳ

※ 製造番号は YYMMSSSS の構成
YY:西暦年下 2 桁、MM:月、SSSS:連番

Ｔ－５５１７１改訂５

裕

板状形圧着端子

－73－

ランプ

ブザー

緑点灯

無

黄点灯

間欠音
（ピッピッピッ）

赤点灯

連続音
（ピー）

（４）中継装置
130
32

32

16

3.5φ穴

3.5

デマンド警報装置
電源

190

中継装置

記名板

通信

ＴＡＫＥＭＯＴＯ
１

1 2 3 4 5 6

モード

AC100V
電源

２
ﾊﾞﾝﾄﾞ

電 源ｺｰﾄﾞ 0.75m㎡
約３ｍ付属

端子カバー
取り外し可能蓋取付
内部に端子台，設定スイッチ取付

入線口

記名板 ケース右側面貼付
製品名
中継装置
形番
ＴＤＤ３ＺＢ－Ｗ
ＡＣ１００Ｖ ５０／６０Ｈｚ
消費電力 １０Ｗ
信号点数 ４点
製造番号 ＹＹＭＭＳＳＳＳ
製造年
２０＊＊年
ＨＡＫＡＲＵ ＰＬＵＳ

※ 製造番号は YYMMSSSS の構成
YY:西暦年下 2 桁、MM:月、SSSS:連番

Ｔ－５５１７１改訂５

－74－

3.5
40

3905±50（５）専用ＣＴ標準タイプ
形式：ＣＴ－Ｓ１
ケーブル長：約 3.9m
端子：F1.25-3（Y 型）

Ｔ－５５１７１改訂５－75－

（６）専用ＣＴ長距離タイプ
形式：ＣＴ－Ｌ１
ケーブル：別途ご準備ください
端子：M3×3（電源・出力・ＣＯＭ）

Ｔ－５５１７１改訂５－76－

（７）専用 CT 長距離タイプ用接続ケーブル
形式：ＣＢ６２－□ケーブル長：形式枝番にて指定（5m または 10m～100m を 10m 単位で指定ください）
端子： F1.25-3（Ｙ型）

指定 m±2%（８）電源コード
形式：ＣＢ６７ケーブル長：約 2.9m
端子：R1.25-3（丸型）
プラグ形状：L プラグ

2905±10030±3（９）電力量計接続線
形式：ＣＢ５９ケーブル長：0.3m
端子：F2-4（Ｙ型）

Ｔ－５５１７１改訂５－77－

（１０）FOMA アダプタ用小型防滴アンテナ
ケーブル長：約 2.5m
端子：SMA コネクタ

１５．使用条件（１） 使用温度－１０～５５℃（２） 使用湿度

３０～８５％ＲＨ（結露無きこと）（３） 設置

直射日光の当たらない場所に設置してください。
塵埃の少ない場所に設置してください。

（４） その他

腐食性ガスのある場所では使用しないでください。

※ 上記範囲外で使用されますと、通信不良や液晶画面表示不良、ひいては機器破損する恐れがありますのでご注意ください。

Ｔ－５５１７１改訂５－78－

１６．お手入れについて
お手入れの際は、必ず電源プラグをコンセントから抜いてください。
本体の表面の汚れやホコリは、乾いた柔らかい布で軽く拭き取ってください。
レンズクリーナーやガーゼなどの柔らかい布でもかまいません。
ご注意※ シンナー、ベンジン、アルコール、ガラスクリーナーなどは絶対に使用しないでください。
故障及び変色や変形の原因になります。
※ 硬いものでこすったり、強い力を加えないでください。
傷がついたり、故障の原因になります。

１７．保管にあたって
長時間使用しないときは、必ず電源プラグをコンセントから抜いてください。
ご注意※ ゴム製品やビニール製品などと長時間接触させないでください。変色や変形の原因になります。

１８．保証期間と保証範囲
納入品の保証期間はご注文主のご指定場所に納入後 1 ヶ年とします。保証期間中に納入者側の責任により故障を生じた場合は、その機器の故障部分の交換，又は修理を納入者側の責任において行います。
本製品は一般産業用途向けです。保証は日本国内においてのみ有効で、次に該当する場合はこの保証の範囲から除外させていただきます。
(1) 需要者側の不適当な取扱ならびに使用による場合、納入者以外の改造または修理による場合。
(2) 故障の原因が納入品以外の事由による場合、その他、天災，災害などで納入者側の責にあらざる場合。
なおここで言う保証は納入品単体の保証を意味するもので、納入品の故障により誘発される損害はご容赦いただきます。

１９．お問い合わせ本社・工場〒532-0027

大阪府大阪市淀川区田川３－５－１１

ハカルプラス株式会社

Ｔ－５５１７１改訂５

ＴＥＬ

０６－６３００－２１１２

ＦＡＸ

０６－６３０８－７７６６－79－