INSTRUCTION MANUALINSTALLATION BASE
BEFORE USE ....

INSTALLATION

Thank you for choosing us. Before use, please check contents of the package you received as outlined below.
If you have any problems or questions with the product,
please contact our sales office or representatives.

Slider■ PACKAGE INCLUDES:
Installation base...................................................................(1)■ MODEL NO.
Confirm Model No. marking on the product to be exactly
what you ordered.

POINTS OF CAUTION■ WIRING• Do not install cables close to noise sources (relay drive
cable, high frequency line, etc.).
• Do not bind these cables together with those in which
noises are present. Do not install them in the same duct.

2345678910Speciﬁcation(side)

Mounting Unit Cursor Key

11121314151617181920Slider

Note: The side of mounting unit lock slot have No. 1 – 10terminal connections.
■ TERMINAL ASSIGNMENT
1IO1
6IO6

■ GENERAL PRECAUTIONS• Before you remove the unit or mount it, turn off the power
supply, input and output signals for safety.
■ ENVIRONMENT• Indoor use.
• When heavy dust or metal particles are present in theair, install the unit inside proper housing with sufficientventilation.
• Do not install the unit where it is subjected to continuousvibration. Do not subject the unit to physical impact.
• Environmental temperature must be within -10 to +55°C(14 to 131°F) with relative humidity within 10 to 90% RH
in order to ensure adequate life span and operation.

1Mounting Unit Lock Slot

■ INSTRUCTION MANUALThis manual describes necessary points of caution when
you use this product, including installation, connection andbasic maintenance procedures.

■ CONFORMITY WITH EU DIRECTIVES• The equipment must be mounted inside the instrument
panel of a metal enclosure.
• The actual installation environments such as panel configurations, connected devices, connected wires, may affect the protection level of this unit when it is integrated
in a panel system. The user may have to review the CE
requirements in regard to the whole system and employ
additional protective measures to ensure the CE conformity.

R10-BS1

MODEL

2
IO2
7
IO71211FEDB1617
SLD DG

345
IO3 IO4 IO58910IO8 IO9 IO1013DA18NC1415NC FE1192024V 0VPINNO.

ID

FUNCTION

1IO1

I/O Terminal 111FE

Modbus ground

2IO2I/O Terminal 212DBDBPINNO.

ID

FUNCTION

3IO3I/O Terminal 313DA

DA

4IO4I/O Terminal 414NC

Unused5

IO5I/O Terminal 515

FE1Power ground

6IO6I/O Terminal 616

SLDShield

7

IO7I/O Terminal 717

DG

DG

8IO8I/O Terminal 818NCUnused

9

IO9I/O Terminal 91924V

Power supply 24V DC10IO10I/O Terminal 10200V

Power supply 0V DC

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-6248 Rev.1

P. 1 / 4

R10-BS1

MOUNTING■ DIN RAIL MOUNTING (SIDE)• Mounting the unitA)Hang the upper hook at the rear side of unit on the DINrail.
B)Push the lower part of the unit in the direction of the arrow until the unit is firmly fixed to the DIN rail.

■ WALL MOUNTING
Referring to “MOUNTING REQUIREMENTS unit: mm[inch]” on page 3, pull out the upper and lower sliders of theunit and fix them with M4 screws (Torque: 1.4 N·m).

AB• Removing the unit
A)Push down the DIN rail adaptor using a minus screwdriver.
B)Pull out the lower part of the unit.
C)Remove the upper part from the DIN rail.

CBA

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-6248 Rev.1

P. 2 / 4

R10-BS1

TERMINAL CONNECTIONSConnect the unit as in the diagram below.

5 [.20] 7 [.28]■ EXTERNAL DIMENSIONS unit: mm [inch]
36 [1.42]

80 [3.15]

234567891011121314151617181920[4 [.16]]

DIN rail(35mm wide)

7 [.28] 5 [.20]

89 [3.50]

145 [1.77]■ MOUNTING REQUIREMENTS unit: mm [inch]■ CONNECTION DIAGRAM

2-M499 [3.90]

I/O module CN

I/O

111 FE

212 DB

313 DA416 SLD517 DG

615 FE1

719 24V DC

820 0V DCModbus

Power input

910

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-6248 Rev.1

P. 3 / 4

R10-BS1

WIRING INSTRUCTIONS FOR BASE
■ SCREW TERMINALTorque: 0.5 N·m■ SOLDERLESS TERMINAL
Refer to the drawing below for recommended ring tongue
terminal size. Spade tongue type is also applicable.
Recommended manufacturer: Japan Solderless TerminalMFG.Co.Ltd, Nichifu Co.,ltd (Solderless terminals with insulation sleeve do not fit)
Applicable wire size: 0.25 to 1.65 mm2
3max

4min

6max

3.2 dia.

(mm)

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-6248 Rev.1

P. 4 / 4