ORBIT 60 SERIES

System Interface Module
Datasheet

Bently Nevada Machinery Condition Monitoring

142M9054 Rev. B

Description
Each Orbit 60 system requires a single System Interface
Module (SIM) The SIM provides the user access to manage
protection configuration, local display, system-level
diagnostics, system LEDs, system contacts, and the system
protection fault relay. The SIM occupies one slot and must be
adjacent to the Power Input Module (PIM) in the chassis.
The SIM is the access point for configuring and maintaining
the system. The module communicates to the Orbit Studioconfiguration software and transmits the configuration toother modules in the system. The SIM provides a physicalaccess security feature through a key-lock switch on thepublic side and a contact on the utility side of the SIM. Eitherof these controls can be used to secure the system
configuration, preventing unauthorized changes.
The SIM has three independently configurable Ethernet ports.
Each port can be used for system configuration, system timesynchronization, temporary troubleshooting, or an external
display.
System level functions include:lllll

Alarm List
System Event List
System Level Diagnostics
Firmware Updates
System Level Controls
o RUN/PROG Modeo Trip Mutiplyo System Alarm Inhibito System Reseto Protection Fault Relay (Output)

ORBIT 60 SERIES System Interface Module
Datasheet

142M9054 Rev. B

System Interface Module (SIM)

System Interface Module
System Interface Module (SIM)Power Consumption

Default CoilState

Normally Energized

Switching
Properties

Limited to non-inductive
loads

Typical

7.6 Watts

Communications

Maximum

10.9 Watts

Alarm Inhibit

1 Ethernet port Independent Ethernet ports- public side
1000/100/10 Base-T Autonegotiation
2 Ethernetports - utilityside

System ResetConnector

RJ-45

Configuration LockSupportedConnections

NTP time sources

System Contacts
4 contacts onutility or rearsideVoltage In

Trip Multiply

24 V max

Current rating <1 mA to 125 mA

Orbit Config - System
configuration
Orbit Display - Local system
display

TriggerThresholdInput High

1.7 V

TriggerThresholdInput Low

0.8 V

Cyber Security

Low Limit
OpenResistance

10.5 to 15.7 kΩ- Encrypted communications using latest TLS
standards.

Upper Limit
ClosedResistance

3.7 to 6 kΩ

- PKI implemented signed firmware images tofacilitate secure boot and trusted firmware
updates.

Cable Length- Aligned to the IEC 62443-4-2 standard.

- Device identity management uses
certificates for trusted connections.

Protection Fault Relay
Relay Type

100 meters (328 feet) max- Configure user, roles and rights accountmanagement.

Solid State, Single-Pole,
Double Throw

Voltage

1 Vdc to 125 Vdc

Current

0.01 to 125 mA

Isolation

250 Volts

Maximum
cycling rate

1 Hz

ORBIT 60 SERIES System Interface Module
Datasheet- Uses physical Run/Program control

2/7

ORBIT 60 SERIES System Interface Module
Datasheet

142M9054 Rev. B

System Interface Module (SIM)SIM LED Indications

Controls and Contacts

OKRSTReset Contactor Button

Used to clear all latchedalarms and NOT OK statuses
across the system. LED
indicates reset contact
closed. 1

OK LED - indicates the operational
status of the module.

LINK

Internal Communication LED successful communication on
the internal network.

SAI
System Alarm
Inhibit Contact

Used to inhibit all alarms
within the system. LED
indicates the state of thealarming functions within thesystem.

ATTN

Attention LED - unacknowledged
system events.

INHB

Inhibit LED - one or more
configured alarming functions
have been inhibited.

TMTrip MultiplyContact

Used to place the system in
Trip Multiply. LED indicatesthat the system is in Trip
Multiply mode.

FAULT

LOCK
Configuration
Lock Contactor Key

PRG - Allows configuration
changes to be made to thesystem. Amber LED indicatesthe system is in Programmode.

Indicates Protection Fault Status.
A green LED indicates that all theprotection functions within thesystem are operational. Red
indicates the protection path isfaulted. A blinking amber lightindicates an unconfiguredmodule.

RUN - Locks the system,
blocking configuration
changes. Green LED
indicates the system is inRun mode. 2NO, ARM, NC
ProtectionFault Relay

NO, ARM, and NC contacts
are all used to wire theoutput to an external
receiver. A green LED
indicates that all theprotection functions within
the system are operational.
Red indicates the protection
path is faulted and theProtection Fault Relay is in atripped state (notenergized).

1 Performed by either closing the contact on themodule or pressing the button on the frontpanel.

2 Performed by either closing the contact on

the module or setting the key on the front to theRUN setting on the front panel.

ORBIT 60 SERIES System Interface Module
Datasheet

3/7

ORBIT 60 SERIES System Interface Module
Datasheet142M9054 Rev. B

Environmental Limits
ChassisOperatingTemperature
Range(indoor useonly)

ModuleTemperature
Rating
Certification

Environmental Limits

3U Chassis:-30°C to +70°C(-22°F to 158°F)
6U Chassis:-30°C to +65°C(-22°F to 149°F)< 2000 m (6,562 ft)

AltitudeHigher altitudes are
possible but are site
specificapplications.
Contact Bently
Nevadasupport if you
require higher
altitudes.

Temperatures over
50°C (122°F) require
forced air convection
with a minimum
airspeed of 0.5 m/s.
-30°C to +70°C(-22°F to 158°F)
When using aBridge module,
temperatures over58°C (136°F) require
forced air
convection with aminimum airspeedof 0.5 m/s.

PollutionDegree

Pollution Degree 2Installation
Category

Category II

Verify that temperature ratings on thewiring cables match the operating
temperature range.

CAUTION
You must still meet
the Chassis
OperatingTemperature Range
defined above.
Storage
Temperature
Range-40°C to +85°C(-40°F to 185°F)

Relative
Humidity

0% to 95% rH non-condensing
operating and storage

Vibration

Without Isolators:
0 g to 0.35 g @ 57-500 Hz

LOCATION TEMPERATURE
AND HUMIDITY
While the system has beentested and capable of achieving
the design life when operating inenvironments up to 70°C,
whenever operating any
electronics system in elevatedhumidity or temperatures
exceeding 40°C, adding
environmental controls
maximizes the operational life ofthe system.

With Isolators:
0 g to 5 g @ 57-500 Hz
Shock

2” Incline Drop

ORBIT 60 SERIES System Interface Module
Datasheet

4/7

ORBIT 60 SERIES System Interface Module
Datasheet

142M9054 Rev. B*MaritimeCompliance and Certifications

ABS Rules for Condition of Classification,
Part 1FCClThis device complies with part 15 of theFCC Rules. Operation is subject to thefollowing two conditions:
lll

Steel Vessels Rules
Offshore Units and Structures*Recorder Output module, Bridge
module, and 6U systems
approvals pending

This device may not cause harmfulinterference.
This device must accept any
interference received, includinginterference that may cause
undesired operation.

Functional Safety
This component is non-interfering withthe safety system. The system SIL 2certification does not require thiscomponent be SIL certified.

EMC

Hazardous Area Approvals

European Community Directive:
EMC Directive 2014/30/EUFor the detailed listing of country andproduct-specific approvals, refer tothe Approvals Quick Reference Guide(108M1756).

Standards:
EN 61000-6-2; Immunity for
Industrial Environments
EN 61000-6-4; Emissions for
Industrial Environments

For additional technicaldocumentation, please log in to
bntechsupport.com and access theBently Nevada Media Library.

Electrical Safety
European Community Directive:cNRTLus

LV Directive 2014/35/EU

Class I, Zone 2: AEx/Ex ec nC IIC T4 Gc;
Class I, Zone 2: AEx/Ex nA nC IIC T4 Gc;
Class I, Division 2, Groups A, B, C, D T4;Class I, Division 2, Groups A, B, C, D T4(N.I.);

Standards:
EN 61010-1;
EN 61010-2-201;

RoHS

T4 @ Ta= -30˚C to +70˚C (-22˚F to +158˚F)

European Community Directive:

ATEX/IECEx

RoHS Directive 2011/65/EU

II 3 G
Ex ec nC IIC T4 Gc
Ex nA nC IIC T4 Gc

Cyber Security
Designed to meet IEC 62443-4-2

T4 @ Ta= -30˚C to +70˚C (-22˚F to +158˚F)

ORBIT 60 SERIES System Interface Module
Datasheet

5/7

ORBIT 60 SERIES System Interface Module
Datasheet

142M9054 Rev. B

Ordering Information
For the detailed listing of country andproduct-specific approvals, refer tothe Approvals Quick Reference Guide(108M1756).
For additional technicaldocumentation, please log in tobntechsupport.com and access theBently Nevada Media Library.

System Interface Module
Ordering Option

Description

60R/SIM01-AAA-B • System Interface
ModuleAAA – Hazardous Area Certifications
00

No Hazardous Area

01

CSA/NRTL/C (Class I,Div 2)

02

Multi (CSA, ATEX,IECEx)

XXXCountry SpecificApprovals

B – SIL Level
0

No SILFor an Orbit 60 safety system, SIL
certification for the SIM is notrequired.

ORBIT 60 SERIES System Interface Module
Datasheet

6/7

ORBIT 60 SERIES System Interface Module
Datasheet

142M9054 Rev. B

Copyright 2024 Baker Hughes Company. All rights reserved.

Bently Nevada, Orbit 60 and Orbit Logo are registered trademarks of Bently Nevada, a Baker Hughes business, in theUnited States and other countries. The Baker Hughes logo is a trademark of Baker Hughes Company. All otherproduct and company names are trademarks of their respective holders. Use of the trademarks does not imply any
affiliation with or endorsement by the respective holders.
Baker Hughes provides this information on an “as is” basis for general information purposes. Baker Hughes does notmake any representation as to the accuracy or completeness of the information and makes no warranties of any
kind, specific, implied or oral, to the fullest extent permissible by law, including those of merchantability and fitness
for a particular purpose or use. Baker Hughes hereby disclaims any and all liability for any direct, indirect,
consequential or special damages, claims for lost profits, or third party claims arising from the use of theinformation, whether a claim is asserted in contract, tort, or otherwise. Baker Hughes reserves the right to makechanges in specifications and features shown herein, or discontinue the product described at any time without
notice or obligation. Contact your Baker Hughes representative for the most current information.
The information contained in this document is the property of Baker Hughes and its affiliates; and is subject tochange without prior notice. It is being supplied as a service to our customers and may not be altered or its content
repackaged without the express written consent of Baker Hughes. This product or associated products may becovered by one or more patents. See Bently.com/legal.

1631 Bently Parkway South, Minden, Nevada USA 89423
Phone: 1.775.782.3611 (US) or Bently.com/support
Bently.com

7/7