MODEL: R30NCIT1
Remote I/O R30 Series

RELATED PRODUCTS

NETWORK MODULE(CC-Link IE TSN)
Functions & Features• Interchanges analog or discrete I/O signals with thefiledbus (CC-Link IE TSN)
• Combined with R3 Series I/O modules
25
[.98]

• PC configurator software (model: R30CFG)• PC configurator software (model: R3CON)• CSP+ file
The configurator software and CSP+ file are downloadable
at our web site.
CSP+ file is also downloadable at CC-Link Partner
Association's web site.
For connecting to PC, use commercially available Mini-Btype USB cable. (provided by user)• R3 series I/O modules (except R3-TC2 and R3S-CM2A)

GENERAL SPECIFICATIONS
110[4.33]

98 [3.86]
mm [inch]

MODEL: R30NCIT1[1]
ORDERING INFORMATION• Code number: R30NCIT1[1]Specify a code from below for [1].
(e.g. R30NCIT1/Q)• Specify the specification for option code /Q(e.g. /C01)[1] OPTIONS
blank: none
/Q: With options (specify the specification)

SPECIFICATIONS OF OPTION: Q
COATING (For the detail, refer to our web site.)/C01: Silicone coating/C02: Polyurethane coating/C03: Rubber coating

Connection
CC-Link IE TSN: RJ-45 connector
Internal bus: Via the Installation Base (model: R30BS)
Internal power: Via the Installation Base (model: R30BS)
Isolation: CC-Link IE TSN to internal bus or internal power
Input type & range:
R30 series I/O module: PC configuration software (model:R30CFG)
R3 series I/O module: PC configuration software (model:R3CON)
Internal bus communication cycle: Approx. 1 msec.
Status indicator: RUN, RD, SD, D LINK, ERR, L ER, LINK
(Refer to the instruction manual.)

CC-Link IE TSN
Protocol: IEEE 802.3
Transmission type: 1000BASE-T
Communication speed: 1 Gbps
Communication method: Time sharing method
Synchronization function: IEEE802.1AS and IEEE1588v2
compliantCertification class: Class B
Network cable: Cable conformed to CC-Link IE Field
Double shielded twist pair cable (CAT5e)
RJ-45 connector
Network topology: Line, star and ring
Max. number stations: 64770 (Total master and slavestation)(Number of max. connectable slaves may vary dependingon the master module. Refer to the instruction manual ofthe master module)
Max. station-to-station distance: 100 m
Station type: Remote station
Link device: RX/RY 112 points, RWw/RWr 64 points(Number of points summation of I/O module for R30 series
and R3 series)

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-8902 Rev.4 Page 1/7

MODEL: R30NCIT1
INSTALLATION
Current consumption: ≤ 160 mA
Operating temperature: -10 to +55°C (14 to 131°F)
Storage temperature: -20 to +65°C (-4 to +149°F)
Operating humidity: 10 to 90 %RH (non-condensing)
Atmosphere: No corrosive gas or heavy dust
Mounting: Installation Base (model: R30BS)
Weight: 125 g (0.28 lb)

PERFORMANCE
Insulation resistance: ≥ 100 MΩ with 500 V DC
Dielectric strength: 1500 V AC @ 1 minute (CC-Link IE TSN
to internal bus or internal power)1500 V AC @ 1 minute (power input to FE; isolated on thepower supply module)

STANDARDS & APPROVALS
Refer to the manuals to comply with the standards.
EU conformity:
EMC Directive
EMI EN 61000-6-4
EMS EN 61000-6-2
RoHS Directive

EXTERNAL VIEW
■ FRONT VIEW

■ SIDE VIEW

Status Indicator LEDs

L ER

RUNRDSDD LINKERR

Speciﬁcations

CN1
L ER LINK

CC-Link IE TSN Communication
RJ-45 Modular Jack

Positioning Guide

LINK

CN2IP Address / Station No. Rotary SW

×16
STATION No.
×1

PC Conﬁgurator Connector
CONFIG■ BOTTOM VIEW

Base Fixing Screw

Lock Tab

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-8902 Rev.4 Page 2/7

MODEL: R30NCIT1DATA ALLOCATIONThis unit recognize type of I/O module (number of occupied station) configured the same base, and assign it to I/O Modules
data with slot order automatically. However, I/O module assignment is performed only when power is turned on, in the case ofchanging configuration of I/O module, please turn on power again.
Keep number of station occupied of I/O module under 64, because max number of occupied station is 64 per a node. When theI/O module has space, data is transmitted close to HOST PC/PLC.
Station type: Remote station
Link device: RX/RY 128points, RWw/RWr 64points(Points are total of R30 series and R3series module)
E.g. I/O data is assigned as shown below in the case of following configuration.
BASE
R30BS08

R30EBS04

SLOT NUMBER
PWR
COM
123456781234MODEL
R30PS1
R30NCIT1
R30SV4
R30US2
R30TS4
R30YV4R30XN16AR30XN16A
R30YN16A
R30YN16A
R3-SV8R3-YV8
R3-DA32A
R3-DC32A

NUMBER OF OCCUPIED STATION––424411118822■ INPUT DATA
The figure below shows the data sent from the device to the master.
15
RWr n+0015
Slot 1

R30SV4+4Slot 2

R30US2+6Slot 3

R30TS4Slot 4

R30YV4

R30BS08+2+8+10+12+14+16+18

Slot 5Slot 6
Slot 7
Slot 8R30EBS04 Slot 1

R30XN16A
R30XN16A
R30YN16A
R30YN16A
R3-SV8+20+22+24Slot 2

R3-YV8+34Slot 3R3-DA32A+36Slot 4R3-DC32A+26■ OUTPUT DATA
The figure below shows the data received from the master.

+28+30+32RWw n+0CH1CH2+2CH3CH4+4CH1CH2+6CH1CH2+8CH3CH4+10CH1CH2+12CH3CH4Di16 points+14Di16 points
Do16 points+16Do16 points
CH1+18CH2CH3+20CH4CH5+22CH6CH7+24
CH8CH1+26CH2CH3+28CH4CH5+30CH6CH7+32CH8+34
Di16 points
Di16 points+36Do16 points
Do16 points

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp0
R30BS08

R30EBS04

Slot 1

R30SV4

Slot 2

R30US2

Slot 3

R30TS4

Slot 4

R30YV4

Slot 5
Slot 6
Slot 7
Slot 8
Slot 1

R30XN16A
R30XN16A
R30YN16A
R30YN16A
R3-SV8

Slot 2R3-YV8

Slot 3

R3-DA32A

Slot 4

R3-DC32A

CH1
CH2
CH3
CH4
CH1
CH2
CH1
CH2
CH3
CH4
CH1
CH2
CH3
CH4
Di16 points
Di16 points
Do16 points
Do16 points
CH1
CH2
CH3
CH4
CH5
CH6CH7
CH8
CH1CH2
CH3CH4CH5CH6CH7CH8
Di16 points
Di16 points
Do16 points
Do16 points

ES-8902 Rev.4 Page 3/7

MODEL: R30NCIT1■ STATUS DATA150
F E D C B A 9 8 7 6 5 4 3 2 1 0
RX(n+0)
Remote READY
RX(n+1)Module Status (R30 Series)

RX(n+2)Module Status (R3 Series)

RX(n+3)

Error Status (R30 Series)

RX(n+4)

Error Status (R3 Series)

RX(n+5)

Data Error Status (R30 Series)

RX(n+6)

Data Error Status (R3 Series)

RX(n+7)

Unused• RX(n+0)0 to 7 is reservation area, RX(n+0)B is used as Ready signal, the bit is “1” when this module is in normal.
RX(n+0)8 to A, RX(n+0)C to F are not used.
When the Ready signal is 0, current input data and status are not reflected correctly.
When the Ready signal is 1, input data and status are determined valid data.
• Module Status
RX(n+1)0 to RX(n+1)F indicate whether individual I/O modules of R30 series are mounted or not .
RX(n+2)0 to RX(n+2)F indicate whether individual I/O modules of R3 series are mounted or not.
The bit corresponding to the mounted slot turns to “1”, and the unmounted slot to “0”.
• Error Status
RX(n+3)0 to RX(n+3)F indicate error status for each module of R30 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is cleared.
However, when the last module is detached, the error bit is held.
R30X16(under development) input power in error or disconnected.
R30Y16(under development) output current in error (e.g. load unconnected)
RX(n+4)0 to RX(n+4)F indicate error status for each module of R3 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is held.
R3-TSx, R3-RSx, R3-US4 input burnout
R3-DA16A input power in error or disconnected
R3-YSx output current error (e.g load unconnected)
R3-PC16A external power supply in error or disconnected• Data Error Status
RX(n+5)0 to RX(n+5)F indicate data error status for each module of R30 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is cleared.
However, when the last module is detached, the error bit is held.
Input value is out of -15% to 115%
R30TS4, R30RS4, R30USx input burnout
RX(n+6)0 to RX(n+6)F indicate error status for each module of R3 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is held.
Input value is out of -15% to 115%
In the case of R3-US4 (voltage input) input level out of -10% to 110%.
RX(n+1)0, RX(n+3)0, RX(n+5)0
RX(n+1)1, RX(n+3)1, RX(n+5)1
RX(n+1)2, RX(n+3)2, RX(n+5)2:
RX(n+1)F, RX(n+3)F RX(n+5)F

R30 series slot 1
R30 series slot 2
R30 series slot 3

RX(n+2)0, RX(n+4)0, RX(n+6)0
RX(n+2)1, RX(n+4)1, RX(n+6)1
RX(n+2)2, RX(n+4)2, RX(n+6)2:
RX(n+2)F, RX(n+4)F, RX(n+6)F

R3 series extension slot 1
R3 series extension slot 2
R3 series extension slot 3

R30 series slot 16

R3 series extension slot 16

Link devices other than the above are not in use.

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-8902 Rev.4 Page 4/7

MODEL: R30NCIT1I/O DATA DESCRIPTIONS■OPERATION IN CASE OF A COMMUNICATION ERROR WITH I/O MODULES
When the communication between the network module and the I/O modules is lost due to an error in an input module, the lastprocess values are held until the communication is re-established.
■ MODULE STATUS, ERROR STATUS, DATA ERROR STATUS
Shows each module's availability and error status.
150

Module 1
Module 2
Module 3:
Module 16■ANALOG DATA (16-bit data, models: R30SV4, R30SV2, R30YV4, R30YS4, R30US4, etc.)
16-bit binary data.
Basically, 0 to 100% of the selected I/O range is converted into 0 to 10000 (binary).
Negative percentage is represented in 2's complements.
150■ ANALOG DATA (16-bit data, models: R30RS4, R30TS4, R30US4, etc.)
16-bit binary data.
With °C temperature unit, raw data is multiplied by 10. For example, 25.5°C is converted into 255.
With °F temperature unit, the integer section of raw data is directly converted into the data.
For example, 135.4°F is converted into 135.
Minus temperature is converted into negative values, represented in 2’s complements.
150■ ANALOG DATA (16-bit data, models: R30CT4E etc.)
16-bit binary data.
Integer obtained by multiplying unit value (A) by 100.
In case of CLSE-R5, integer obtained by multiplying unit value (A) by 1000.
150■ ANALOG DATA (16-bit data, models: R3-PA2, PA4A, WT1, WT4, etc.)
150+0Lower 16 bit
15+10Higher 16 bit

32-bit binary data is used for accumulated counts, encoder positions, and active energy.
Lower 16 bits are allocated from the lowest address to higher ones, higher 16 bits in turn.
32-bit data cannot be accessed using floating addresses.

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-8902 Rev.4 Page 5/7

MODEL: R30NCIT1■ ANALOG DATA (32-bit data, models: R3-BA32A, BC32A, etc.)
32-bit binary data is used for BCD.
Lower 16 bits are allocated from the lowest address to higher ones, higher 16 bits in turn.
32-bit data cannot be accessed using floating addresses.
150+0Lower 16 bits
150+1

Higher 16 bits

■ 16-POINT DISCRETE DATA (models: R30XN16A, R30YN16x, etc.)
150

Input 1 (Output 1)
Input 2 (Output 2)
Input 3 (Output 3)::
Input 16 (Output 16)
0 : OFF
1 : ONEXTERNAL DIMENSIONS unit: mm [inch]
98 [3.86]

110 [4.33]

25 [.98]

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-8902 Rev.4 Page 6/7

MODEL: R30NCIT1SCHEMATIC CIRCUITRY & CONNECTION DIAGRAMSTATUS STATION NO. SETTINGROTARY SW
IND. LED

IsolationComm.
Circuit

RJ-45 MODULAR JACKIsolation
CC-Link IE TSN CN2

PC CONFIGURATORCONNECTORControlCircuit

RJ-45 MODULAR JACKINTERNAL BUS
CONNECTOR

CC-Link IE TSN CN1

INTERNAL POWER

USB CONNECTOR

Regarding CN1 and CN2 of RJ-45 connector for CC-Link IE TSN network, there is no restriction for connection order.

Specifications are subject to change without notice.

R30NCIT1 SPECIFICATIONS

MG CO., LTD.
www.mgco.jp

ES-8902 Rev.4 Page 7/7