INSTRUCTION MANUALNETWORK MODULE

MODEL(CC-Link IE TSN network)

R30NCIT1

BEFORE USE ....

POINTS OF CAUTION

Thank you for choosing us. Before use, please check contents of the package you received as outlined below.
If you have any problems or questions with the product,
please contact our sales office or representatives.

■ CONFORMITY WITH EU DIRECTIVES• The equipment must be mounted inside the instrument
panel of a metal enclosure.
• The actual installation environments such as panel configurations, connected devices, connected wires, may affect the protection level of this unit when it is integrated
in a panel system. The user may have to review the CE
requirements in regard to the whole system and employ
additional protective measures to ensure the CE conformity.

■ PACKAGE INCLUDES:
Network module...................................................................(1)■ MODEL NO.
Confirm Model No. marking on the product to be exactly
what you ordered.
■ INSTRUCTION MANUALThis manual describes necessary points of caution whenyou use this product, including installation, connection andbasic maintenance procedures.
■ CSP+ file
CSP+ file is downloadable at our web site or CC-Link Partner Association’s web site (https://.cc-link.org).

■ HOT SWAPPABLE MODULES• It is possible to replace a module with the power supplied
provided that the module is replaced with one with thesame model number and installed in the same base slot.
• Be sure to replace a module when it is not communicatingwith the host as it may affect the system. Note that replacing multiple modules at one time may greatly changeline voltage levels. We strongly recommend to replacethem one by one.
■ ENVIRONMENT• Indoor use.
• When heavy dust or metal particles are present in theair, install the unit inside proper housing with sufficientventilation.
• Do not install the unit where it is subjected to continuous
vibration. Do not subject the unit to physical impact.
• Environmental temperature must be within -10 to +55°C(14 to 131°F) with relative humidity within 10 to 90% RH
in order to ensure adequate life span and operation.
■ WIRING• Do not install cables close to noise sources (relay drive
cable, high frequency line, etc.).
• Do not bind these cables together with those in which
noises are present. Do not install them in the same duct.
■ R3 I/O MODULE EXTENSION• The internal bus communication period for R3 series I/Omodules installed on the R30EBS is as follows.
Internal bus communication period = 6 msec. x number ofI/O module + 10 msec. (Data update period of main CPU)
Example: Four R3 I/O modules
6 msec. x 4 + 10 msec. = 34 msec.
Even when the R30EBS is mounted to the R30BS, theinternal bus communication period of R30 series is kept
to approx. 1 msec.
■ AND ....
• The unit is designed to function as soon as power is supplied, however, a warm up for 10 minutes is required forsatisfying complete performance described in the datasheet.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 1 / 17

R30NCIT1COMPONENT IDENTIFICATION■ FRONT VIEW

■ SIDE VIEW

Status Indicator LEDs

Positioning Guide

Speciﬁcations

CN1
L ER LINK

CC-Link IE TSN Communication
RJ-45 Modular JackL ER

RUNRDSDD LINKERR

LINK

CN2IP Address / Station No. Rotary SW×16
STATION No.
×1

PC Conﬁgurator ConnectorCONFIG■ BOTTOM VIEW

Base Fixing Screw

Lock Tab■ STATUS INDICATOR LED
ITEM
StatusIndicator

CN1CN2ID

COLOR

FUNCTION

RUNGreenDevice StateRD

Green

Receiving Data

SD

GreenSending Data

D LINK

Green

Data link
Transmitting

ERR

Red

Error

LINK

Green

CN1 Linking Up

L ER

Red

CN1 Receiving Data

LINK

Green

CN2 Linking Up

L ER

Red

CN2 Receiving Data

STATUS
ON
OFF
ON
OFF
ON
OFF
ON
Blinking
OFF
ON
Blinking
OFFON
OFFON
OFF
ON
OFF
ON
OFF

DESCRIPTION
NormalDevice error
Receiving
Unreceived data
Sending
UnsentIn action (Cyclic transmitting)In action(Stopping cyclic transmitting)*1
Not complied with
Critical failure*²
Minor failure*³
NormalLinking up
Link-down
Abnormality receiving data
Normality receiving data
Linking up
Link-down
Abnormality receiving data
Normality receiving data

*1. Setting as reservation area, stop linking and etc..
*2. Host communication error, internal bus communication error etc.
*3. Non-volatile memory error, or IP address / station No. setting rotary switch has been changed after turning on the module.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 2 / 17

R30NCIT13 4 56

BCDE

3 4 567 8 9AF 01 27 8 9AF 01 2■ IP ADDRESS / STATION NO. SETTING ROTARY SW
Set the fourth octet of IP address and station No. with two rotary switches. The upper rotary SW sets the upper digits (MSB),
and the lower rotary SW sets the lowest digit (LSB) with hexadecimal (configurable range is 1 to 254).
Turn off the power supply when setting IP address / Station No. setting Rotary SW, as the setting is activated when turningon the power supply.
Confirm available station numbers in the manual of the master unit (Factory default setting: 01H).
IP address: The first to third octet are common with the first to third octet of IP address for master station.
For setting MSB of Station No. (×16)
For setting LSB of Station No. (×1)

BCDE

* Station No. setting example

IP address / Station No. setting rotary SW are set with hexadecimal.
For example, in the case of setting station No. 175, Set the Station MSB: A and LSB: F.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4P. 3 / 17

R30NCIT1

INSTALLATION■ INSTALLATION TO THE BASE
Use the Installation Base (model: R30BS).
The mounting slot for the network card is fixed to COM.
Do not mount the network card to any other slot.
PWR COM

I/O1■ HOW TO REMOVE THE MODULE
1) Loosen the base fixing screw using a screwdriver (stemlength: 70 mm/2.76” or more).

I/O nBaseFixing Screw■ HOW TO MOUNT THE MODULE
1) Engage the positioning guide of the module with the Installation Base.
2) Pivot the module on the positioning guide and press itdown until the lock tab clicks into place.

2) While pressing the projection on the lock tab, push themodule upward.
3) Detach the positioning guide of the module from the Installation Base.

Positioning GuideLock Tab

3) Tighten the base fixing screw using a screwdriver (stemlength: 70 mm/2.76” or more) (torque 0.5 N·m).

BaseFixing Screw

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 4 / 17

R30NCIT1TERMINAL CONNECTIONSConnect the unit as in the diagram below.
■ EXTERNAL DIMENSIONS unit: mm [inch]
98 [3.86]

110 [4.33]

25 [.98]

CC-Link IE TSN CN1 RJ-45 MODULAR JACK
CC-Link IE TSN CN2 RJ-45 MODULAR JACKPC CONFIGURATORCONNECTOR

USB CONNECTOR

BUS CONNECTOR■ CONNECTION DIAGRAM

INTERNAL BUS

INTERNAL POWER

Regarding CN1 and CN2 of RJ-45 connector for CC-Link IE TSN network,
there is no restriction for connection order.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 5 / 17

R30NCIT1TRANSMISSION DATA DESCRIPTIONSThis unit recognize type of I/O module (number of occupied station) configured the same base, and assign it to I/O Modules
data with slot order automatically. However, I/O module assignment is performed only when power is turned on, in the caseof changing configuration of I/O module, please turn on power again. Keep number of station occupied of I/O module under64, because max. number of occupied station is 64 per a node.
When the I/O module has space, data is transmitted close to HOST PC/PLC.
Station type: Remote station
Link device: RX/RY 128 points, RWw/RWr 64 points (points are total of R30 series and R3 series module)
For example, the configuration is as below, data areas are assigned as shown below.
BASE
R30BS08

R30EBS04

SLOT NUMBERPWRCOM
123456781234MODEL
R30PS1
R30NCIE1
R30SV4
R30US2
R30TS4
R30YV4
R30XN16A
R30XN16A
R30YN16A
R30YN16A
R3-SV8R3-YV8
R3-DA32A
R3-DC32A■ INPUT DATA
The figure below shows the data sent from the device to the master.
1515
R30SV4+4Slot 2

R30US2+6Slot 3

R30TS4Slot 4

R30YV4

R30BS08+2+8+10+12+14+16+18Slot 5
Slot 6Slot 7
Slot 8R30EBS04 Slot 1

R30XN16A
R30XN16A
R30YN16A
R30YN16A
R3-SV8+20+22+24+26■ OUTPUT DATAThe figure below shows the data received from the master.

0Slot 1RWr n+0

NUMBER OF OCCUPIED STATION––424411118822Slot 2

R3-YV8+34Slot 3

R3-DA32A+36Slot 4

R3-DC32A+28+30+32

RWw n+0CH1CH2+2CH3CH4+4CH1CH2+6CH1CH2+8CH3CH4+10CH1CH2+12CH3CH4+14Di16 points
Di16 points
Do16 points+16
Do16 points+18CH1CH2+20CH3CH4+22CH5CH6+24CH7CH8+26CH1CH2+28CH3CH4+30CH5CH6+32CH7CH8+34Di16 points
Di16 points+36
Do16 points
Do16 points

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPAN0R30BS08

R30EBS04

Slot 1

R30SV4

Slot 2

R30US2

Slot 3

R30TS4

Slot 4

R30YV4

Slot 5
Slot 6
Slot 7
Slot 8
Slot 1

R30XN16A
R30XN16A
R30YN16A
R30YN16A
R3-SV8

Slot 2R3-YV8

Slot 3

R3-DA32A

Slot 4R3-DC32A

EM-8902 Rev.4

CH1CH2CH3CH4CH1CH2CH1CH2CH3CH4CH1CH2CH3CH4
Di16 points
Di16 points
Do16 points
Do16 points
CH1CH2CH3CH4CH5CH6CH7CH8CH1CH2CH3CH4CH5CH6CH7CH8Di16 points
Di16 points
Do16 points
Do16 points

P. 6 / 17

R30NCIT1■ STATUS DATA150
F E D C B A 9 8 7 6 5 4 3 2 1 0
RX(n+0)
Remote READY
RX(n+1)Module Status (R30 Series)

RX(n+2)Module Status (R3 Series)

RX(n+3)

Error Status (R30 Series)

RX(n+4)

Error Status (R3 Series)

RX(n+5)

Data Error Status (R30 Series)

RX(n+6)

Data Error Status (R3 Series)

RX(n+7)

Unused• RX(n+0)0 to 7 is reservation area, RX(n+0)B is used as Ready signal, the bit is “1” when this module is in normal.
RX(n+0)8 to A, RX(n+0)C to F are not used.
When the Ready signal is 0, current input data and status are not reflected correctly.
When the Ready signal is 1, input data and status are determined valid data.
• Module Status
RX(n+1)0 to RX(n+1)F indicate whether individual I/O modules of R30 series are mounted or not .
RX(n+2)0 to RX(n+2)F indicate whether individual I/O modules of R3 series are mounted or not.
The bit corresponding to the mounted slot turns to “1”, and the unmounted slot to “0”.
• Error Status
RX(n+3)0 to RX(n+3)F indicate error status for each module of R30 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is cleared.
However, when the last module is detached, the error bit is held.		 R30X16(under development) input power in error or disconnected.		 R30Y16(under development) output current in error (e.g. load unconnected)		 RX(n+4)0 to RX(n+4)F indicate error status for each module of R3 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is held.		 R3-TSx, R3-RSx, R3-US4 input burnout		 R3-DA16A input power in error or disconnected		 R3-YSx output current error (e.g load unconnected)		 R3-PC16A external power supply in error or disconnected• Data Error Status
RX(n+5)0 to RX(n+5)F indicate data error status for each module of R30 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is cleared.
However, when the last module is detached, the error bit is held.		 Input value is out of -15% to 115%		 R30TS4, R30RS4, R30USx input burnout
RX(n+6)0 to RX(n+6)F indicate error status for each module of R3 series.
The bit corresponding to such module turns to “1”, as described below.
When the each module is detached, the error bit is held.		 Input value is out of -15% to 115%		 In the case of R3-US4 (voltage input) input level out of -10% to 110%.			 RX(n+1)0, RX(n+3)0, RX(n+5)0			 RX(n+1)1, RX(n+3)1, RX(n+5)1			 RX(n+1)2, RX(n+3)2, RX(n+5)2						:			 RX(n+1)F, RX(n+3)F RX(n+5)F

R30 series slot 1
R30 series slot 2
R30 series slot 3			 RX(n+2)0, RX(n+4)0, RX(n+6)0			 RX(n+2)1, RX(n+4)1, RX(n+6)1			 RX(n+2)2, RX(n+4)2, RX(n+6)2						:			 RX(n+2)F, RX(n+4)F, RX(n+6)F

R3 series extension slot 1
R3 series extension slot 2
R3 series extension slot 3

R30 series slot 16

R3 series extension slot 16

Link devices other than the above are not in use.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 7 / 17

R30NCIT1

I/O DATA DESCRIPTIONS■ OPERATION IN CASE OF A COMMUNICATION ERROR WITH I/O MODULES
When the communication between the network module and the I/O modules is lost due to an error in an input module, thelast process values are held until the communication is re-established.
■ MODULE STATUS, ERROR STATUS, DATA ERROR STATUS
150

Module 1
Module 2
Module 3:
Module 16■ ANALOG DATA (16-bit data, models: R30SV4, R30SV2, R30YV4, R30YS4, R30US4, etc.)
16-bit binary data.
Basically, 0 to 100% of the selected I/O range is converted into 0 to 10000 (binary).
Negative percentage is represented in 2’s complements.
150■ ANALOG DATA (16-bit data, models: R30RS4, R30TS4, R30US4, etc.)16-bit binary data.
With °C temperature unit, raw data is multiplied by 10. For example, 25.5°C is converted into 255.
With °F temperature unit, the integer section of raw data is directly converted into the data. For example, 135.4°F is converted into 135.
Minus temperature is converted into negative values, represented in 2’s complements.
150■ ANALOG DATA (16-bit data, models: R30CT4E etc.)
16-bit binary data.
Integer that engineering unit value (A) multiplied by 100 (for CLSE-R5, integer that engineering unit value (A) multipliedby 1000).
150■ ANALOG DATA (32-bit data, models: R3-PA2, PA4A, WT1, WT4, etc.)
32-bit binary data is used for accumulated counts, encoder positions and active energy.
Lower 16 bits are allocated from the lowest address to higher ones, higher 16 bits in turn.
150Lower 16 bits+0
150
Higher 16 bits+1■ ANALOG DATA (32-bit data, models: R3-BA32A, BC32A, etc.)
32-bit binary data is used for BCD.
Lower 16 bits are allocated from the lowest address to higher ones, higher 16 bits in turn.
150
Lower 16 bits+015+10
Higher 16 bits

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 8 / 17

R30NCIT1■ DISCRETE DATA (models: R30XN16A, R30YN16x, etc.)
150

Input 1 (Output 1)
Input 2 (Output 2)
Input 3 (Output 3)::
Input 16 (Output 16)
0 : OFF
1 : ON

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 9 / 17

R30NCIT1

SETTING■ SUMMARY
Follow the setting procedure below for configuring R30NCIT1 by using GX Works3 of Mitsubishi Electric (hereinafter referredto as GX Works3).
■ REGISTRATION FOR PROFILEThis unit supports CC-Link Family system profile (CSP+).
CSP+ can be downloaded from the our web site or CC-Link Partner Association’s web site (https://www.cc-link.org).
However, registration of CSP+ is optional. If CSP+ is not needed, skip this section and move on to [Construction of System].
1) Start GX Works3.

2) From the main menu, select [Tool] ➞ [Register Profile].

Click3) Select the downloaded CSP+ file, and click [Register] to finish registration.

Click

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 10 / 17

R30NCIT1■ CONSTRUCTION OF SYSTEM
The below figure shows an exemplary configuration of line connection.
CC-Link IE TSN

USB cable

MasterStationLocal
StationPC
GX Works3

Remote Station

Remote Station(R30NCIT1)

1) Master station, Local Station and Remote Station (R30NCIT1) are connected by Ethernet cable. CN1 and CN2 of CC-Link
IE TSN Network RJ-45 modular jacks can be connected in any order.
Before wiring, make sure to turn off the power of each unit.
2) After wiring is completed, turn on each unit.
■ CREATION OF PROJECT
Connect the PC and the master station, and create a project of the master station with GX Works3 installed in the PC.
1) Start GX Works3.
2) From the main menu, select [Project] ➞ [New] to create a new project.

Select3) Select the series, type, and program language, and click OK.

Click

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 11 / 17

R30NCIT14) In the following window, when [Module Label: Not use] is displayed in Module Setting, click [Setting Change] to open theoption window, and change to [Use].

Click

Select [Yes] for [Use Module Label] in [Operation Setting], and click [OK].

Click

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 12 / 17

R30NCIT15) Double click [Module Configuration] in the Navigation window to open the [Module Configuration] window. According tothe real PLC configuration, select the module from [POU List] of the [Element Selection] window, and drag and drop it tothe module configuration diagram.

Drag & Drop

6) Double click [CC-Link IE TSN network module] to open the parameter setting window.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 13 / 17

R30NCIT17) Set Station Type to [Master Station], Network No. to 1 in [Required Settings].

8) Click <Detailed Setting> of [Network Configuration Settings] in [Basic Settings] to display the [CC IE TSN Configuration]
window

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 14 / 17

R30NCIT1
According to the real system configuration, select the device from [Module List], and drag and drop it to the device configuration diagram. Click [Close with Reflecting Setting].
* When CSP+ not registered, select [General CC IE TSN Module].

ClickDrag & Drop9) Click <Detailed Setting> of [Refresh Setting] to display the Refresh Setting window

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 15 / 17

R30NCIT1
Assign link devices RX/RY/RWr/RWw to devices of the CPU unit, click [Apply] to close the window.

Click10) Click [Convert] ➞ [Convert] to execute conversion.

SelectMG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 16 / 17

R30NCIT111) Click [Write to PLC...] in [Online] on menu bar to open [Online Data Operation] window.

SelectCheck necessary items, and click [Execute].

Click

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-8902 Rev.4

P. 17 / 17