920MHz 帯 無線信号伝送ユニット（1 対 N 通信 分散モード）

UMIO-411 取扱説明書

本製品を正しくご利用いただくためにこの取扱説明書をよくお読みください。
Version 1.01

株式会社アローセブン

目次
1 はじめに ··································································································································11.1 警告表示 ···························································································································11.2 安全上のご注意とお断り ········································································································12 概要 ·······································································································································32.1 UMIO-411AXS とは ··············································································································32.2 製品一覧 ···························································································································42.3 特長··································································································································42.4 外観図 ······························································································································53 製品仕様 ·································································································································63.1 一般仕様 ···························································································································63.2 端子台 ······························································································································73.2.1 適合線サイズ ··················································································································73.2.2 端子台説明 ····················································································································7[デジタル入力信号]···············································································································8[デジタル出力信号]···············································································································8[アナログ入力] ····················································································································83.3 モニタ－LED 表示 ················································································································93.3.1 通常動作 ·······················································································································93.4 寸法図 ···························································································································· 104 動作設定 ······························································································································· 114.1 電源の接続 ······················································································································ 114.1.1 AC アダプタによる電源供給 ······························································································· 114.1.2 端子台による電源供給 ···································································································· 114.2 ジャンパーピン ··················································································································· 114.3 UMS 設定ソフトによる設定 ···································································································· 124.3.1 端末情報 ····················································································································· 144.3.2 端末設定内容 ··············································································································· 144.3.3 端末操作 ····················································································································· 144.4 周波数一覧 ······················································································································ 154.5 設定例 ···························································································································· 164.5.1 マスター側設定 ·············································································································· 174.5.2 スレーブ側設定·············································································································· 175 動作説明 ······························································································································· 185.1 1 対 N 通信 ······················································································································· 185.2 1 対 N 点数分散モード ········································································································· 195.2.1 １点分散動作時の I/O 対応表 ···························································································· 205.2.2 ２点分散動作時の I/O 対応表 ···························································································· 215.2.3 ４点分散動作時の I/O 対応表 ···························································································· 22

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）
6 アンテナタイプ ························································································································· 23
6.1 UMIO-411AXS + 可倒式アンテナ ·························································································· 23
6.2 UMIO-411AXS + プレート付アンテナ ······················································································ 23
6.3 UMIO-411AXS + フランジアンテナ ························································································· 23
7 本製品を使用する上での注意点 ·································································································· 24
8 アフターサービス ····················································································································· 252

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

1 はじめに
1.1 警告表示
記号の意味
危険警告
注意

誤った取扱いをした場合、死亡または重傷を負う危険性があり、その切迫の度合いが高いことを示します。
誤った取扱いをした場合、死亡または重傷を負う危険性があることを示します。
誤った取扱いをした場合、傷害を負うことが想定されるか、または物的損害に関して知っておいてほしい内容を示します。

1.2 安全上のご注意とお断り

警告◼

本体内部に異物を入れないでください。また、水などの液体が入らないように注意してください。故障、感電、火災の原因になります。

◼

分解しないでください。修理技術者以外の人は、絶対に分解や、修理・改造は行わないでください。感電の危険があります。また、発火などの異常動作でケガをすることがあります。

◼

落とさないようにしてください。
本体は安定した場所に設置してください。誤って落としたりすると、破損やケガなどの恐れがあります。

注意◼

指示された電源で使用してください。

◼

使用・保管上の注意
高温・多湿の場所、長時間直射日光の当たる場所での使用・保管は避けてください。
また、周辺の温度変化が激しいと、内部結露によって誤動作する場合があります。

◼

設置場所の注意
衝撃や振動の加わりやすい場所での使用・保管は避けてください。故障の原因になります。

1

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）－ お断り －◼

本製品を医療機器、航空機等には使用しないでください。もし、ご使用になる場合は当社までご相談ください。

◼

当社は品質の向上に努めておりますが、半導体製品は故障、誤動作する場合があります。
本製品の故障または誤動作によって結果的に、人身事故、火災事故等が発生しないよう安全設計に十分ご注意願います。

◼

この取扱説明書の記載内容は、2021 年 12 月現在のものです。
記載内容を予告なく変更あるいは製造中止することがありますのでご了承ください。

◼

無線通信は外来のノイズ、障害物等により一時的に通信できなくなることがあります。このような時でも安全に稼動するようにシステム設計してください。
また、その場合データの収集ができない場合があります。

◼

本製品は日本国内専用です。

2

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

2 概要
2.1 UMIO-411AXS とはＩ／Ｏ信号とアナログ信号 1 点を無線伝送する装置です。
1 対 N 通信のスレーブ側として、信号点数が少ない場合に、廉価版として使用することができます。
各動作設定は、USB（仮想 COM）を使用し、UMS 設定ソフトにより行います。

3

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

2.2 製品一覧
製品名UMIO-411AXS

特長
デジタル入出力 920MHz 帯無線モデム内蔵 外部アンテナタイプ

アンテナ（AXS タイプ使用可能）
UAS-AM01

920MHz 帯 可倒式アンテナ（屋内用） アンテナ長さ：全長 約 108mm

UAS-AK01

920MHz 帯 可倒式アンテナ（屋内・屋外用） アンテナ長さ：全長 約 204mm

UAS-PK01

920MHz 帯 プレート付可倒式アンテナ ケーブル 1ｍ

UAS-PK02

920MHz 帯 プレート付可倒式アンテナ ケーブル 2ｍ

UAS-FK01

920MHz 帯 フランジ可倒式アンテナ ケーブル 1m

UAS-FK02

920MHz 帯 フランジ可倒式アンテナ ケーブル 2m

電源用供給用 AC アダプタ（各機種共通）
UMD-ACA12AC アダプタ 12V

2.3 特長
◼

920MHz 帯無線データ伝送です。

◼

免許の申請、資格が不要です。

◼

アンテナは用途に応じて、選択可能です。

◼

信号線の接続はスクリューレスのプッシュタイプで配線が容易です。

◼

入力信号点数 4 点（フォトカプラ入力）です。

◼

アナログ入力信号点数 1 点（DC0～5V または 0～20mA）です。

◼

出力信号点数 1 点（オープンコレクタ出力）です。

◼

電源は DC9-28V または AC アダプタ（DC12V）が使用できます。

◼

LED モニターにて動作状態が確認できます。

4

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

2.4 外観図モニターLEDUSB 接続コネクタ

アンテナ

AC アダプタ用コネクタ

信号接続端子台5

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

3 製品仕様3.1 一般仕様
項目

内容

電源電圧

DC9V～28V または、専用 AC アダプタ

消費電流 (DC12V 時)

50mA 以下＜入出力仕様＞
デジタル入力デジタル出力アナログ入力

点数

4

入力形式

フォトカプラ 無電圧接点

点数

1

出力形式

オープンコレクタ シンク型

電流容量200mA／点

耐電圧

30V

点数

1

入力信号レンジ

電圧入力 DC0～5V または電流入力 0～20mA

最大定格入力入力抵抗

電圧入力時：－0.5V～＋6.5V
電流入力時：－1mA～25mA
電圧入力時：≧10MΩ
電流入力時：250Ω

分解能

12 ビット精度±0.2% F.S.

＜通信ポート＞
USB -MicroB

PC 設定用＜無線部仕様＞
技術基準

ARIB STD-T108 適合証明取得済み

空中線電力20mW

電波形式

F1D

無線周波数帯920.6MHz～928.0MHz

データ変調速度50kBps

通信距離 （ 環境による ）屋外見通し環境 1200m（アンテナ UAS-AK01［地上高 2m］使用時）＜その他＞
重量約 130g

外形サイズ

寸法図参照

動作温度-10℃ ～ +50℃

6

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

3.2 端子台3.2.1 適合線サイズ
単線(㎟)

より線(㎟)AWG

推奨むき線長さ(㎜)0.2-1.5

0.2-1.5

16-2483.2.2 端子台説明端子台

名称

内容

IN 1

デジタル入力 1

IN 2

デジタル入力 2

IN 3

デジタル入力 3

IN 4

デジタル入力 4

OUT 1

デジタル出力 1GND

GND

A1-IN

アナログ信号入力 1A1-GND

アナログ信号入力 1 GND

DC9-28V

外部電源入力／出力兼用GND

外部電源 GND

7

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）[デジタル入力信号]

入力状態

電気的状態

OFF

デジタル入力 n – GND 間がオープン

ON

デジタル入力 n – GND 間がショート[デジタル出力信号][アナログ入力]

8

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

3.3 モニタ－LED 表示

3.3.1 通常動作
LED

色機能

内容

POWER

赤電源モニター

電源 ON 時点灯

MON1

赤状態モニター

通常消灯

MON2

緑

無線通信モニター

送信時 20ms 点灯

MON3

緑

無線通信モニター

受信時 20ms 点灯

STATUS

緑

無線通信モニター

通信エラー発生時 点滅(0.5s)

IN 1- IN 4

赤デジタル入力 1-4 モニター

入力 ON 時点灯／OFF 時消灯

OUT 1

緑

デジタル出力 1 モニター

出力 ON 時点灯／OFF 時消灯

3.3.2 内部エラー
内部エラー発生時は、異常検出後以下のモニター表示をして動作停止します。
異常内容

LED

色機能動作設定異常

MON1

赤点滅(0.1s)

内部不揮発性メモリ異常

STAT

緑点滅(0.1s)

内部エラーが発生した場合は、弊社までお問合せ下さい。

9

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

3.4 寸法図10

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

4 動作設定4.1 電源の接続
4.1.1 AC アダプタによる電源供給
専用の AC アダプタをご使用ください。やむを得ずその他のＡＣアダプタを使用する場合には下記のものをお使いください。
DC13.5V 2A EIAJ TYPE4

4.1.2 端子台による電源供給
端子台 の DC9-28V 端子、GND 端子に入力してください。

本端子は AC アダプタの入力端子と接続されています。
AC アダプタとの同時入力はしないでください。
USB ケーブル接続しても電源は供給されません。AC アダプタまたは、端子台より電源供給をお願いします。

4.2 ジャンパーピン

JP3

名称

内容JP3

アナログ入力選択

短絡箇所

機能

無電圧入力（0-5V）

有電流入力（0-20mA）出荷時設定

ジャンパーピンは機器の電源が OFF の状態で変更してください。

11

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

4.3 UMS 設定ソフトによる設定
以下の設定は UMS 設定ソフトで機器毎に個別設定する必要があります。
Windows PC に“UMS 設定ソフト”をインストールします。UMIO-411AXS に電源を供給し、PC と USB ケーブルで接続します。ご使用の PC にシリアル USB ドライバがインストール済みだと、シリアルポートが追加されます。
UMS 設定ソフトを起動します。
（ご使用の PC にシリアル USB ドライバが必要です。）

USB ケーブル A オス-ＭｉｃｒｏB オス
UMIO-411AXS
Windows PC

電源入力

UMS 設定ソフト

AC アダプタ又は DC

UMS 設定ソフトを起動すると以下の画面が表示されます。

UMIO-411AXS と接続した「COM ポート」をリストから選択し、「端末接続」ボタンをクリックします。

12

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）
正常に接続すると以下の詳細設定画面が表示されます。
接続が失敗した場合は、機器の接続構成、電源状態を再確認後、「端末スキャン」ボタンをクリックして、接続の確認を行ってください。

13

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

4.3.1 端末情報
機器の機種情報やソフトウェアバージョンなどが表示されます。

4.3.2 端末設定内容
内容
動作PAN ID周波数
ポーリング間隔

説明

設定範囲

機器の動作設定を行います。使用する組み合わせでマスターとスレーブが１対マスター／スレーブ／リピータとなるようにして下さい。
無線グループの設定行います。使用する組み合わせで同一の PANID を設定00h～FFhする必要があります。
無線の周波数の設定を行います。使用する組み合わせで同一の周波数を設0～37定する必要があります。(周波数一覧参照)
マスター機がポーリングを送信するタイミングを設定します。

0~255[ ×0.1 秒 ]スレーブ台数(マスター時）

マスターがポーリングするスレーブの台数を設定します。

1～32

中継ルート設定

中継機器を使用する場合に設定します。

-

スレーブの機器 ID を設定します。同一環境では重複しないように設定して下

1～32（マスター設定時のみ）（マスター設定時のみ）
スレーブ ID(スレーブ時）

リピータ ID(リピータ時）

通信エラー判定回数（マスター時）
ポート出力論理

通信エラー判定時間

さい。
リピータの機器 ID を設定します。同一環境では重複しないように設定して下さ

33～48

い。
マスター側が各スレーブに対し、無線通信ができなくなり通信エラー処理を開始

1～99するまでの判定回数を設定します。本設定回数連続してスレーブからの応答がない場合は通信エラー処理を行います。
デジタル出力ポートの出力論理を選択します。

正論理／負論理

無線通信ができなくなり通信エラー処理を開始するまでの時間を設定します。

1～60[秒]

本設定時間無線通信が行われない状態が継続すると通信エラー処理を行います。

通信エラー時出力
ステータス出力

無線通信エラー処理において、デジタル出力ポートの状態を選択します。出力OFF／保持ポートの状態を保持したい場合は保持を選択します。
UMIO-411AXS では、ステータス出力端子がない為、無効です。

-4.3.3 端末操作
各パラメータを変更後、書き込みボタンで書き込みを実行します。書き込み実行後、再起動ボタンで端末を再起動するか、電源 OFF→ON により再起動してください。
内容

説明

読出し

端末の設定内容を参照し、PC 画面に表示します。

書込み

PC 画面の設定を端末に送信し、端末は設定保存します。

無線通信テスト

無線通信テスト用の画面を開きます。

再起動

端末の再起動をします。

14

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

4.4 周波数一覧
周波数番号

使用周波数［MHz］

周波数番号

使用周波数［MHz］

0920.6

19924.4

1920.820924.6

2921.021924.8

3921.222925.04921.423925.2

5921.624925.4

6921.825925.6

7922.026925.8

8922.227926.09922.428926.2

10922.629926.4

11922.830926.6

12923.031926.813923.2

32927.014923.4

33927.2

15923.6

34927.4

16923.835927.6

17924.036927.8

18924.2

37928.0

15

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

4.5 設定例
1 点分散動作時でマスター側(UMIO-88AXS)とスレーブ（UMIO-411）を 8 台使用する場合（1 対 8 通信）（UMIO-AXS：スレーブ 1）[機器構成]
UMIO-88AXS：マスター（UMIO-AXS：スレーブ 2）（UMIO-AXS：スレーブ 3）（UMIO-AXS：スレーブ 4）（UMIO-AXS：スレーブ 5）（UMIO-AXS：スレーブ 6）（UMIO-AXS：スレーブ 7）（UMIO-AXS：スレーブ 8）[I/O 対応表]

機器設定

マスター

内容対応

IN1→

OUT1

←

IN2→

OUT2

←

IN3→

OUT3

←

IN4→

OUT4←

IN5→

OUT5←

IN6→

OUT6

←

IN7→

OUT7

←

IN8→

OUT8←

16

機器設定
スレーブ 1

スレーブ 2

スレーブ 3

スレーブ 4

スレーブ 5

スレーブ 6

スレーブ 7

スレーブ 8

内容OUT1IN1
OUT1IN1
OUT1IN1
OUT1
IN1
OUT1
IN1
OUT1
IN1
OUT1IN1
OUT1IN1

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

4.5.1 マスター側設定4.5.2 スレーブ側設定※上記はスレーブ 1 設定時です。スレーブ 2～8 に設定する場合は、スレーブ ID を２～8 に変更し、書き込みします。

17

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

5 動作説明5.1 1 対 N 通信
マスター側機器から各スレーブ側機器にスレーブ使用台数分、無線ポーリングを行います。
無線通信データに入出力信号を付加することで、マスター、スレーブ間の信号伝送を行います。
マスター機器に中継ルートを登録してある場合は、中継ルートに従い通信を行います。
中継ルートにリピータ機器が登録されている場合は、無線データ受信時、次の宛先に転送します。
マスター側の無線送信間隔は UMS 設定ソフト「ポーリング間隔」設定により変更可能です。
内容

設定値

説明

マスター側ポーリング間隔

0.3[秒]UMS 設定ソフト「ポーリング間隔」設定により変更可能です。

Tpoll

最速で 0.2[秒]まで設定可能です。

マスター側応答タイムアウト

0.2[秒]

Ttout

マスター側ポーリング送信後、スレーブからの応答を監視する時間です。
この時間スレーブからの応答を受信できない場合に、マスターは次のポーリング送信を行います。リピータ使用時は、中継段数に応じて延長されます。

マスター

無線通信
スレーブ 1

Tpol

スレーブ 2

Tpol

スレーブ 3・・・
Ttout

スレーブ N×

スレーブ 1・・・

無線通信するマスター機器とスレーブ機器及びリピータ機器では周波数、PANIDが同じ設定である必要があります。周波数の変更が必要な場合はそれぞれの機器に対し、UMS 設定ソフトを使用し、設定を行ってください。

18

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

5.2 1 対 N 点数分散モード
1：N 分散モードの動作では、マスター側 I/O に対し、各スレーブの I/O が分散され反映されます。
以降はマスター機器 UMIO-88(入力 8 点、出力 8 点)、スレーブ機器に UMIO-411(入力 4 点、出力 1 点)を使用する場合の組み合わせとなります。
スレーブ機器動作モード

分散点数1 対 N 1 点分散モード

11/1

1 対 N 2 点分散モード

22/1

1 対 N 4 点分散モード

44/1

有効点数 IN/OUT

分散点数は出荷時の動作設定により決定します。必要な構成での分散点数を弊社までお知らせください。

19

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

5.2.1 １点分散動作時の I/O 対応表
機器設定

マスター

拡張１

内容対応

IN1→

OUT1

←

IN2→

OUT2

←

IN3→

OUT3←

IN4→

OUT4←

IN5→

OUT5←

IN6→

OUT6←

IN7→

OUT7←

IN8→

OUT8←

IN1→

OUT1←

IN2→

OUT2←

IN3→

OUT3←

IN4→

OUT4←

IN5→

OUT5←

IN6→

OUT6←

IN7→

OUT7←IN8→

OUT8←

機器設定
スレーブ 1
スレーブ 2
スレーブ 3
スレーブ 4
スレーブ 5
スレーブ 6
スレーブ 7
スレーブ 8
スレーブ 9
スレーブ 10
スレーブ 11
スレーブ 12
スレーブ 13
スレーブ 14
スレーブ 15
スレーブ 16

内容対応

OUT1

内容

機器設定

IN1→

IN1

OUT1←

OUT1

IN2→

IN1

OUT2←

OUT1

IN3→

IN1

OUT3←

OUT1

IN4→

IN1

OUT4←

拡張 2

OUT1

IN5→

IN1

OUT5←

OUT1

IN6→

IN1

OUT6←

OUT1

IN7→

IN1

OUT7←

OUT1

IN8→

IN1

OUT8←

OUT1

IN1→

IN1

OUT1←

OUT1IN2→

IN1

OUT2←

OUT1

IN3→

IN1

OUT3←

OUT1

IN4→

IN1OUT4←

拡張 3OUT1IN5→

OUT5←

OUT1IN6→

IN1

OUT6←

OUT1IN7→

IN1

OUT7←

OUT1IN8→

IN1

OUT8←

IN120

機器設定
スレーブ 17
スレーブ 18
スレーブ 19
スレーブ 20
スレーブ 21
スレーブ 22
スレーブ 23
スレーブ 24
スレーブ 25
スレーブ 26
スレーブ 27
スレーブ 28
スレーブ 29
スレーブ 30
スレーブ 31
スレーブ 32

内容OUT1IN1
OUT1IN1
OUT1IN1
OUT1IN1
OUT1
IN1
OUT1
IN1
OUT1
IN1
OUT1
IN1
OUT1
IN1
OUT1IN1
OUT1
IN1
OUT1
IN1
OUT1IN1
OUT1IN1
OUT1IN1
OUT1IN1

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

5.2.2 ２点分散動作時の I/O 対応表
機器設定

マスター

拡張 1

拡張 2

拡張 3

内容対応

IN1→

OUT1～2←

IN3→

OUT3～4←IN5→

OUT5～6←

IN7→

OUT7～8←IN1→

OUT1～2←

IN3→

OUT3～4←IN5→

OUT5～6←

IN7→

OUT7～8←IN1→

OUT1～2←

IN3→

OUT3～4←IN5→

OUT5～6←

IN7→

OUT7～8←IN1→

OUT1～2←

IN3→

OUT3～4←IN5→

OUT5～6←

IN7→

OUT7～8←

機器設定
スレーブ 1
スレーブ 2
スレーブ 3
スレーブ 4
スレーブ 5
スレーブ 6
スレーブ 7
スレーブ 8
スレーブ 9
スレーブ 10
スレーブ 11
スレーブ 12
スレーブ 13
スレーブ 14
スレーブ 15スレーブ 16

内容対応OUT1

内容機器設定

IN1→

IN1～2

OUT1～2←

OUT1IN3→

IN1～2

OUT3～4←

拡張 4OUT1IN5→

OUT5～6←

OUT1

IN7→

IN1～2

OUT7～8←

IN1～2

OUT1

IN1→

IN1～2

OUT1～2←

OUT1IN3→

OUT3～4←

IN5→

IN1～2

OUT5～6←

OUT1

IN7→

IN1～2

OUT7～8←

OUT1

IN1→

IN1～2

OUT1～2←

OUT1

IN3→

OUT3～4←IN5→

OUT5～6←

OUT1

IN7→

IN1～2

OUT7～8←OUT1IN1→

IN1～2

OUT1～2

←

OUT1

IN3→

IN1～2

OUT3～4←

IN1～2

拡張 5OUT1

IN1～2拡張 6

OUT1
IN1～2

拡張 7

OUT1IN5→

IN1～2

OUT5～6←

OUT1IN7→

IN1～2

OUT7～8←21

機器設定
スレーブ 17
スレーブ 18
スレーブ 19
スレーブ 20
スレーブ 21
スレーブ 22
スレーブ 23
スレーブ 24
スレーブ 25
スレーブ 26
スレーブ 27
スレーブ 28
スレーブ 29
スレーブ 30
スレーブ 31
スレーブ 32

内容OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2OUT1
IN1～2
OUT1
IN1～2
OUT1
IN1～2OUT1
IN1～2OUT1
IN1～2
OUT1
IN1～2UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

5.2.3 ４点分散動作時の I/O 対応表
機器設定

マスター

拡張 1

拡張 2

拡張 3

拡張 4

拡張 5

拡張 6

拡張 7

内容対応

IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←IN1→

OUT1～4←IN5→

OUT5～8←22

機器設定
スレーブ 1
スレーブ 2
スレーブ 3
スレーブ 4
スレーブ 5
スレーブ 6
スレーブ 7
スレーブ 8
スレーブ 9スレーブ 10
スレーブ 11
スレーブ 12
スレーブ 13
スレーブ 14
スレーブ 15
スレーブ 16

内容OUT1IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4OUT1
IN1～4

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

6 アンテナタイプ
本製品で使用可能なアンテナは以下のような形式があります。

6.1 UMIO-411AXS + 可倒式アンテナ
UMIO-411AXS に可倒式アンテナを接続します。
防滴・防塵が必要な場所でご使用の際は、樹脂ケースに入れてご使用ください。

6.2 UMIO-411AXS + プレート付アンテナUMIO-411AXS にプレート付アンテナを接続します。本体を盤ケース内、アンテナを外部に取り付ける場合などにこのタイプを使用します。写真は、プレート付アンテナと、マグネット金具を接続したものです。

6.3 UMIO-411AXS + フランジアンテナ
UMIO-411AXS にフランジ可倒式アンテナを接続します。本体を盤ケース内、アンテナを外部に取り付ける場合などにこのタイプを使用します。

23

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

7 本製品を使用する上での注意点◼ 金属製の物体の近くにアンテナを設置すると、通信距離が短くなることがありますので、なるべく離して設置してください。
◼ 本製品を屋外で使用する場合には防水ケースに入れるなどの対策が必要です。屋内であっても、湿気の多い場所、オイルミストや塵の多いところでは、防水ケースなどに入れて保護してください。
◼ 無線通信状態が良好な場所に本製品を固定してください。（設置する前に通信状態を確認してください。）◼ 本製品に強い力が加わると、破損する恐れがあります。
◼ 異なるユニットのアンテナ間は、できるだけ離してください。アンテナが近いと相互に影響し合うため、それぞれの無線通信に影響を与え、無線区間の再送が増加し通信可能距離が低下します。アンテナ間は 2m 以上離して設置してください。
◼ 同一エリアで本製品を 2 セット以上動作させる場合は、無線周波数を変えて使用して下さい。電波干渉の原因となります。

24

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）

8 アフターサービス◼ 保証期間中の場合、保守規定ならびに保証書の記載内容に基づいて修理いたします。
◼ 保証期間経過後の場合、修理によって機能が維持できる場合はご要望により有料修理いたします。
◼ 備品の供給年限について本製品の補修用部品の供給及び保守対応の期限は、製造打ち切り後 5 年です。
ただし、供給年限内であっても、部品メーカーの生産及び市場供給が途絶えた場合などについては対応できない場合があります。
補修用部品の供給及び保守対応は、原則的に上記期限で終了いたしますが、供給期限経過後であっても必要部品の入手等が可能な場合には、納期および価格についてご相談させていただきます。

修理・点検・アフターサービスについては購入先または弊社までお問い合わせください。

25

UMIO-411 取扱説明書（920MHz 帯 1 対 N 通信 分散モード）
2021 年 12 月 27 日

Version 1.01

株式会社 アローセブン〒 433－8122 静岡県浜松市中区上島 3 丁目 27 番 7 号
Tel : 053（469）0031
Fax : 053（469）0037
Web サイト : https://www.arrow7.co.jp/