200200 ProTIM-R
Datasheet

163662 Rev. AK

Bently Nevada Machinery Condition Monitoring
Description

The 200200 dual-input ProTIM-R (DIN rail mount) provides 2channels of measurement. All acceleration-to-velocity (A-V)
channels condition the signal from an accelerometer andintegrate it to velocity units. The low frequency A-V channels
are better suited for slower speed applications. A-V withAcceleration Enveloping (AE) channels provide both
integrated velocity units and advanced AE signal
conditioning. Temperature channel types include K-type
thermocouples and 100W Platinum (Pt) RTDs with electricalisolation. Each channel is independent and specified when
the ProTIM is ordered.
Table 1: ProTIM Measurement Types and Transducers
Measurement TypeInterfaced
Transducer

Acceleration-to-Velocity (General
Purpose)200150

Low Frequency Acceleration-toVelocity

200155

Acceleration-to-Velocity with AE

200157K-type Thermocouple

2001251

2, 3, or 4 Wire Platinum RTD

Industry standard

Rack Buffered Output (RBO)

Monitor

Process Variable (PV)MonitorPressure

120M1644

Displacement

330101/330103

200200 ProTIM-R
Datasheet

163662 Rev. AK

Specifications
All specifications are at +25 ± 5° C(+77 ± 9° F) unless otherwise specified.
Operation outside the specified limits
will result in false or inaccurate
readings.
Table 1: ProTIM and Transducers Frequency
Responses
DeviceLower Freq
1 Hz

1 KHz

200200-05

1 Hz

1 KHz

200200-06 AV 1 Hz

1 KHz 1

200200-06 AE

500 Hz 1

1 Hz± 15% at 80 Hz

Frequency
Response1

10 Hz to 1 kHz (600 cpm to
60,000 cpm) ± 20% (± 2 dB)1

Not OK Range

Open transducer signal,
power, or common is “Not OK”.
Shorted leads are “Not OK”
except for SIG+ shorted to
SIG- or common shorted toshield.

1 This Frequency response represents the System ProTIM& Transducer. For details on individual device frequency
response, see Table 1: ProTIM and Transducers
Frequency Responses

Upper Freq

200200-01

Accuracy

Electrical: Low Frequency A–V
Channels (with 200155)
Measurement 0 to 50 mm/s pk
Range(0 to 2 in/s pk)
Over Range

63 mm/s pk(2.5 in/s pk)

200150 XDCR

10 Hz

1 KHz

200155 XDCR

3 Hz

10 KHz 2

Resolution

0.025 mm/s
(0.001 in/s pk) nominal

200157 XDCR

10 Hz

10 KHzAccuracy±15% at 80 Hz

Frequency
Response 1

3 Hz to 1 kHz (180 cpm to 60,000cpm) ± 10%(±0.9 dB) 2

Not OK Range

Open transducer signal,
power, or common is “Not OK”.
Shorted leads are “Not OK”
except for SIG+ shorted to
SIG- or common shorted toshield.

1 2002XX-06 ProTIM AE circuitry allows enveloping input

frequency up to 10 KHz.

2 200155 has a long settling time. Therefore, it should

only be used for low frequency acceleration to velocity
channel types.

200200 ProTIM-R and 200150,
200155, 200157 or 200125 transducer
systems
For detailed specification on the transducers,
refer to the individual transducer data sheets.

1 This Frequency response represents the System ProTIM& Transducer. For details on individual device frequency
response, see Table 1: ProTIM and Transducers
Frequency Responses

Electrical: A–V (General Purpose)
Channels (with 200150)

2 The A-V circuitry attenuates frequencies above 1 kHz.

Use of the 200155 transducer to obtain higher frequency
information will be ineffective.

Measurement 0 to 50 mm/s pk
Range(0 to 2 in/s pk)
Over Range

63 mm/s pk (2.5 in/s pk)

Resolution

0.025 mm/s
(0.001 in/s pk) nominal

2/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

Electrical: A–V w/ AE Channels (with200157)

Device200150 200155

200157

OK 3

Great

200200-06

N/A

Measurement
Range

0 to 50 mm/s pk(0 to 2 in/s pk)

Over Range

63 mm/s pk(2.5 in/s pk)

Resolution

0.025 mm/s
(0.001 in/s pk) nominal

Accuracy±15% at 80 Hz

KHz, but 200150 operates only up to 1 KHz.

Frequency
Response 1 A-V

10 Hz to 1 kHz (600 cpm to
60,000 cpm) ± 20%(± 2.0 dB) 2

Electrical: Temperature Channels

AE

10 Hz to 500 Hz (600 cpm to
30,000 cpm) ± 20% (±2.0dB) 3

Not OK Range:

1 ProTIM does not offer AE capability and will only

accept frequencies up to 1 KHz whereas 200157 will
go up to 10 KHz.
2 Lower transducer limit is 10 Hz, whereas 200155 will

operate down to 3 Hz.

3 ProTIM's AE circuit accepts frequencies up to 10

Measurement
Range-18°C to +204°C(0°F to +400°F)

Resolution

0.07°C (0.12°F)

Accuracy

Open transducer signal,
power, or common is “Not
OK”. Shorted leads are“Not OK” except for SIG+
shorted to SIG- orcommon shorted toshield.

1 This Frequency response represents the System

ProTIM & Transducer. For details on individual device
frequency response, see Table 1: ProTIM andTransducers Frequency Responses.

K-Type TC±8°C (±14°F), including
ProTIM-R, thermocouple &lead wire error, maximum
length of 6 meters.
Maximum temperature ramp
rate: ±0.5°C/min.

RTD±4.45°C (±8°F), RTD lead wireerror not included

OK Range-31°C to +213°C (-25°F to+415°F)

Not OK
Condition

Temperatures outside the OK
Range
Open RTD or thermocouple
wires are "Not OK"

2 The A-V circuitry attenuates frequencies above 1

kHz. Use of the 200157 transducer to obtain higher
frequency information will be ineffective. AE signals
up to 10 kHz are processed at the ProTIM.
3 The 500 Hz filter has a 4-pole attenuation slope. The

enveloped signal will range between 1Hz to 500 Hz. Not
OK Range: Open

RTD Compensation Coefficient Alpha in
W/W/°C

Table 2: ProTIM and Transducers
Compatibility

European

0.00385

US Industrial

0.00392

Device200150 200155

200157

200200-01

Great

N/A

OK 1

200200-05

OK 2

Great

OK 2

SoftwareAt host computer
Compensation

3/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

Electrical: Pressure Channels

Electrical: Rack Buffered Output
Channels

Measurement
0 to 50mV
Range

Measurement AC: 1Vpp to 8Vpp full scaleRange
DC: 0 to –20Vdc
Input Signal

Full Scale

OverRange

LOAC_IN

1.6Vpp

1.92Vpp

HIAC_IN

8Vpp

9.6VppDCGAP_IN

DC: -20VDC
AC: 1Vpp

DC: -24.4VDC
AC: See Note

Resolution

10Hz to 3 KHz (+0 to –5%)

Not OK
Range

Input signal is out of range,
Input signal mis-wired.

Electrical: Process Variable
Channels
Measurement Current: +4mA to +20mA
Range
Voltage: +1Vdc to 5Vdc
Current: <+3mA or >+22mA
Voltage: <+0.8Vdc or >+5.5Vdc

Resolution±1% of full-scale value Typical

OK Range

Current: Over +3.2mA
Voltage: Over 0.8Vdc

Frequency
Response

DC to 3 KHz

OK Range

1Vdc to 3Vdc Bias fromtransducer

Frequency
Response

Less than 3 KHz

Measurement 0.1 to 600 Hz
Range(6 to 36000 RPM)

AC over range of DCGAP_IN
occurred when [Vpp(AC)/2 + (1Vdc*0.15) - 2.5V] > 2.181V

Over Range±8.5% of the transducer fullscale rating (transducer
accuracy not included)

Keyphasor Rotational Speed
Channels (with 330101/330103)

AC: ±1% of full-scale value at
100Hz
DC: ±500 mV, absolute accuracy

Frequency
Response

Resolution

4/18

Transducer
Range

10 to 50 mils
(0.254 to 1.27 mm)

Resolution

1 RPM

Accuracy

Within 0.015% of true RPM.

Frequency
Response

Minimum Trigger Width 9.0
mm (0.35 in)
Minimum Trigger Relief 1.25
mm (0.05 in)

Not OK Range

Open/short transducer signal,
Power or common is “Not OK”.

200200 ProTIM-R
Datasheet

163662 Rev. AK

Displacement Channels(with 330101/330103)
Input

shaft diameters smaller than
76.2 mm (3 in) will generally
result in a change in scale
factor. Consult Performance
Specification 159484 foradditional information.

Used with our 3300 XL 8 mmprobe or 3300 5 mm probe andextension cable (5 metre
system) only.

OutputVoltage
Range-3.0 to 3.0 V (Over Specified
linear range)

Transducer
LinearRange

10 to 50 mils (0.254 to 1.27 mm)

Scale
Factor

120 mV/mil +/-10%

Accuracy
Over gap
Range+/-1.2 mils @ mid-scale range.

Frequency
Response

DC to 3 KHz (0 to 180,000 cpm).

Minimum
Target Size

15.2 mm (0.6 in) diameter (flattarget)Not OK
Range

Open/short transducer signal,
Power or common is “Not OK”.

Environmental Limits
Standard: -40°C to +85°C(-40°F to +185°F)
Operating
RTD, K-Type TC and
Temperature Thermocouple pro-TIM have alimited operating temperatureof -25° C to +85° C.
Storage-40°C to +100°C
Temperature (-40°F to +212°F)
100% non-condensing
Apply DC4 grease onconnecter contacts to improve
environmental performanceand prevent corrosion.

Humidity

Minimum: 50.8 mm (2 in)
EnclosureType

Recommended minimum: 76.2
mm (3 in)

Shaft
Diameter:Type 4

MechanicalMeasurements on shaft
diameters smaller than 50 mm(2 in) usually require close
spacing of radial vibration oraxial position transducers withthe potential for theirelectromagnetic emitted fields
to interact with one another(cross-talk), resulting inerroneous readings. Careshould be taken to maintainminimum separation oftransducer tips, generally atleast 40 mm (1.6 in) for axial
position measurements or 74
mm (2.9 in) for radial vibration
measurements. Radial vibrationor position measurements on

Housing
Material

Powder-coated Aluminum

Weight

545 g (19 oz)

Polyester Housing Dimensions
Dimensions or Stainless Steel Housing
Dimensions on pages 13 & 14.

5/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

200151 and 200152 Transducer
Cables

85033 Trendmaster SPA/TIM line
cable

Use to connect the acceleration transducers
to the ProTIM-R.

Use to connect a Signal Processing Adapter(SPA) to the ProTIM. For substitutions, reference
guide 101206.

-20°C to +100°C(-4°F to +212°F).
OperatingTemperature

OperatingTemperature

Note:These cables may be
used at lower temperatures
down to –40°C (-40°F), if thecable is not allowed to moveor flex. Flexing these cables attemperatures below –20°C (4°F) may damage them.

Minimum
Bend Radius

63.5 mm (2.5 in)Construction

4-conductor (22 AWG) with
foil shield and drain wire
(100% coverage), polyvinyl
chloride (PVC) outer jacket.

4x 18 AWG stranded tinned
copperConductors

Shielding

200152 Cables

1x 18 AWG stranded copper,
tinned overcoat uninsulated
drain wire
100% aluminum Mylar foil out
with helically applied drain
wire
85% braided tinned copper

Insulation

Connectors

200151 Cables-70°C to +200°C(-94°F to +392°F).

Screw-on, 5-pin, keyed
connector on the ProTIM-R
end and a PT06F8-4S (orequivalent) on thetransducer end. Connector
coupling nuts consist of 1/220 UNF-threaded 2011 T3
aluminum or UV-stabilized
black nylon. Contact
material is gold-plated
nickel-coated brass.

Conductors

Fluoroethylene propylene(FEP) Teflon material 0.25 mm(0.010 in) thickOuter

FEP Teflon material 0.38 mm(0.015 in) thickClassifications

NEC article 725 class 3
UL Listed

Voltage rating 300 Vrms
Capacitance

PT06F8-4S (or equivalent) on
the transducer end; stripped
stranded wire at ProTIM end.
Connector coupling nut
material is 1/2-20 2011 T3
aluminum or UNF-threaded
nickel-plated brass.
Connector contact material
is gold-plated brass.

Cable assembly meets ULClassifications: 2238. Cable meets IP67
ingress protection.

6/18

BetweenConductors

131 pF/m (40 pF/ft.)

BetweenConductor
and Drain
Wire

262 pF/m (80 pF/ft)

200200 ProTIM-R
Datasheet

163662 Rev. AK

Compliance andCertifications
FCC
This device complies with part 15 of the
FCC Rules. Operation is subject to thefollowing two conditions:llThis device may not cause harmfulinterference.
This device must accept any
interference received, includinginterference that may cause
undesired operation.

EMC
EN 61000-6-2 :2005
EN 61000-6-4:2007 +A1:2011
EMC Directive 2014/30/EU

RoHS
RoHS Directive 2011/65/EU

ATEX
EN 60079-0: 2012/A11:2013
EN 60079-11:2012
EN 60079-15:2010
EN 60079-28:2015 (DSM 149744 only)
EN 60079-31:2014 (TMGI 162459-01 only)
ATEX Directive 2014/34/EU

Maritime
ABS 2009 Steel Vessels Rules
1-1-4/7.7,4-8-3/1.11.1,4-9-7/13

7/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

II (1) G [Ex ia Ga] IIC

Hazardous Area Approvals
TMGI(162459-01)

For the detailed listing of country andproduct specific approvals, refer tothe Approvals Quick Reference Guide(108M1756) available from Bently.com.

T4 @ Ta = -20°C to +65°C

CSA/NRTL/C (Approval Options 05)
Ex ia IIC T4 Ga
Installed withintrinsicallysafe zener
barriers per
drawing
112M7732

Installed
without
barriers per
drawing
112M7732

Class I Zone 0: AEx ia IIC T4 Ga
Class I, Div 1 Groups A, B, C & D
Class II, Groups E, F & GClass III
T4 @ -40° C[ Ta [+ 100° C(-40° F [ Ta [+212° F)
Ex nA IIC T4 Gc
Class I Zone 2: AEx nA IIC T4
GcClass I, Div 2 Groups A, B, C
&D
T4 @ -40° C [ Ta[+ 100° C(-40° F[Ta [+212° F)

ATEX/IECEx
ProTIMs(200200 and200250)II(1) D [Ex ia Da] IIIC
II 3 (1) G Ex nA [is Ga] IIC T4 Gc
II 3(1) D Ex tc [ia Da] IIIC T140°c
Dc IP5X

II 1 G Ex ia IIC T4 GC
II 1 G Ex ia IIC T4 GC
II 3 G Ex nA IIC T4 Gc
T4 @ Ta = -40°C to +100°C
II 3 G Ex nA IIC T4 GC

Trendmaster II 3(3) G Ex nA [ic] IIC T4 Gc
DSM (149744) II 3(3) G Ex nA op is [op is T4 Gc]
IIC T4 Gc
T4 @ Ta = -20°C to +65°C

8/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

Ordering Information
For the detailed listing of country andproduct specific approvals, refer tothe Approvals Quick Reference Guide(108M1756) available from Bently.com.

A: Channel AA Input Option

02

K-Type Thermocouple (200125)103

2 or 3 Wire Pt. RTD

04

4 Wire Pt. RTD

05

Low Freq Accel-to-Velocity(200155)

06

Accel to Velocity w/AE (200157)

07

Rack buffered Output

08

Process Variable

09

Pressure (120M1644)

10

Keyphasor (330101/330103)

11

Displacement (330101/330103)

Acceleration to Velocity (200150)

02

K-Type Thermocouple (200125)103

2 or 3 Wire Pt. RTD

04

4 Wire Pt. RTD

05

Low Freq Accel-to-Velocity(200155)

06

Accel to Velocity w/AE (200157)

07

Rack buffered Output

Pressure (120M1644)

11

Displacement (330101/330103)

01

None

05

Multiple Approvals

1 The 200125 is the recommended Trendmaster sensor

for temperature measurements when the range of a Ktype thermocouple is adequate. We do not recommend
the use of other K-type thermocouples due to theunique electrical isolation requirements of theTrendmaster system, and highly recommend the use of
only non-grounded RTDs and non-grounded tip
thermocouples to prevent ground loops. Failure tocomply may result in Not OK or NO DATA conditions,inaccurate readings, or ProTIM-R damage. Consult thefactory for further information.

Transducer Cable (for use with
200150, 200155, and 200157
Accelerometers)
200151-AA-BB-CC
Use the 200151 with the 200200 ProTIM onlywith applications using either a 142485
Housing Cable Adapter or a 141887 Conduit
Cable Adapter.

B: Channel BB Input Option
01

09

C: Approvals

200200-AA-BB-CC

Acceleration to Velocity (200150)

Process Variable

BB option availability is dependent on AA
options chosen. Not all BB options areavailable with each AA option.

ProTIM-R

01

08

A: Cable Length:20

2.0 metre (6.6 feet) cable40

4.0 metre (13.1 feet) cable60

6.0 metre (19.7 feet) cable

B: Outer Jacket Option:
02

Blue, unarmored

03

Blue, armored

C: Additional Features:

9/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

00Standard coupling nut

Pressure Transducer

02

Nylon coupling nut

120M1644-AAAA

10

Knurled coupling nut

A: Pressure rating

Transducer Cable (for use with
200150, 200155, and 200157
accelerometers)

0030

0 to 30 PSI SG

0050

0 to 50 PSI SG

0100

0 to 100 PSI SG

0300

0 to 300 PSI SG

A: Cable Length:

0500

0 to 500 PSI SG

04

4.0 metre (13.1 feet) cable

1000

0 to 1000 PSI SG

15

15.0 metre (49.2 feet) cable

1500

0 to 1500 PSI SG

25

25.0 metre (82.0 feet) cable (foruse with 200150 only)

2000

0 to 2000 PSI SG

200152-AA-BB

Accessories

B: Additional Features:
00

Standard coupling nut

10

Knurled coupling nut

138493-01

Replacement DIN-mount
mounting pad.

136806-01

T-TIM Assembly.

141887-01

Single Conduit Cable Adapter.

120M1648 -AA (for use with 120M1644
pressure transducer)

141887-02

Double Conduit Cable Adapter.
See Dual Conduit Cable Adapter.

A: Cable Length:142485-01

Anodized aluminum housing
Cable Adapter. See Housing
Cable Adapter.

149831-01

Trendmaster DSM Datasheet.

163986-01

ProTIM-R Installation Manual.

164045Extra Female Terminal Plugs. For
TIM line connections.

164046Extra Male Terminal Plugs. For
TIM line connections.

164352

T-Connector. For splitting TIM
line cable into 2 directions.

85033-0100

150 Meter (500 ft) Cable. For TIM
line, no connectors.

Transducer Cable05

0.5 metre (1.6 feet) cable10

1.0 metre (3.3 feet) cable15

1.5 metre (4.9 feet) cable20

2.0 metre (6.6 feet) cable40

4.0 metre (13.1 feet) cable60

6.0 metre (19.7 feet) cable

90

9.0 metre (29.5 feet) cable

10/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

85033-0200

300 Meter (1000 ft) Cable. For TIM
line, no connectors.

88312-01

4-unit IS Polyester W/P Housing.
Div 1, Type 4X. Houses 4 ProTIM-R
units maximum. See Polyester
Housing Dimensions.

88313-01

2-unit IS Polyester W/P Housing.
Div 1, Type 4X. Houses 2 ProTIM-R
units maximum. See Polyester
Housing Dimensions.

88314-01

4-unit IS SST W/P Housing. Div1,Type 4X, Houses 4 TIMs
maximum. See Stainless Steel
Housing Dimensions.

88315-01

2-unit IS SST W/P Housing. Div 1,Type 4X. Houses 2 TIMs
maximum. See Stainless Steel
Housing Dimensions.

85716-01

2-unit Polyester W/P Housing.
Div 2, Type 4X. Houses 2 ProTIMR units maximum. See Polyester
Housing Dimensions

85717-01

4-unit Polyester W/P Housing.
Div 2, Type 4X,. Houses 4 ProTIMR units maximum. See Polyester
Housing Dimensions.

00500128

Terminal Connector. For
Transducer inputs into ProTIM-R.

02180005

Jumper. For the RTD ProTIM-R
terminals.

03814237

Conduit Hub. 1/2-14 NPT.

03817040

Bonding and Ground Wedge. 1/2
NPT.

03839129

Conduit Fitting. 1/2-14 NPT.

03839240

Cable Seal. 1/4-12 NPT. Diameter
5.0 to 6.7 mm (0.20 to 0.26 in);.
Use with 200152 cable.

03839241

Cable Seal. 1/4-12 NPT. Diameter
1.9 to 3.4mm (0.07 to 0.13 in).

11/18

03839242

Cable Seal. 1/4-12 NPT. Diameter
3.4 to 5.0 mm (0.13 to 0.20 in).
Use with 200125 armoredthermocouple.

03839243

Cable Seal. 1/2-14 NPT. Diameter
6.4 to 7.9 mm (0.25 to 0.31 in).

03840490

Thread Seal. For 1/4 -12 NPT
fittings.

03880243

Square Cut O-ring. For 1/2-14 NPT
fittings.

04500006

Dow Corning 4, ElectricalInsulating Compound (5.3 Oz).

200200 ProTIM-R
Datasheet

163662 Rev. AK

Graphs and Figures
Table 1: Channel Types Cross-compatibility

Note: All dimensions in millimetres (inches) except as noted.

12/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

1.
2.
3.
4.

Top view
Side view
Side view #2
Powder coated aluminum housing

Figure 1: ProTIM Dimensional Diagram

13/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

1. Side view. ProTIM Enclosure Dimensions for dimensions.
2. Top view. ProTIM Enclosure Dimensions for dimensions.
3. If not using Quick Release, use 10-32 pan head screw (2places).
Figure 2: Polyester Housing Dimensions

Table 2: ProTIM Enclosure Dimensions
Part number

Overall (L x W)

Mounting (G x H)

J

K

Q

85716-01 (2-position) 165 x 165 (6.50 x 6.50)

171 x 102 (6.75 x 4.00)

82.5 (3.25) 25.4 (1.00) 143 (5.64)

88313-01 (2 position)

165 x 165 (6.50 x 6.50)

171 x 102 (6.75 x 4.00)

82.5 (3.25) 25.4 (1.00) 143 (5.64)

85717-01 (4 position)

267 x 216 (10.50 x 8.50) 273 x 152 (10.75 x 6.00) 125 (4.94)

33.3 (1.31)

244 (9.61)

88312-01 (4 position)

267 x 216 (10.50 x 8.50) 273 x 152 (10.75 x 6.00) 125 (4.94)

33.3 (1.31)

244 (9.61)

14/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

1. Side view. Stainless Steel ProTIM Enclosure Dimensions for
dimensions.
2. Top view. Stainless Steel ProTIM Enclosure Dimensions for
dimensions.
3. 8 mm (0.31 in) diameter, 4 places
The number of clamps and the placement is shown for the large enclosure. The small enclosure has
only one clamp, centered on the side opposite the hinge.
Figure 3: Stainless Steel Housing Dimensions
Table 3: Stainless Steel ProTIM Enclosure Dimensions
Part number

Overall (L x W)

Mounting (G x H)

Box Size (A x B x C)

88315-01 (2-position) 191 x 176 (7.50 x 6.94)

171 x 102 (6.75 x 4.00)

152 x 152 x 102 (6.00 x 6.00 x 4.00)

88314-01 (4 position)

292 x 227 (11.50 x 8.94) 273 x 152 (10.75 x 6.00) 254 x 203 x 152 (10.00 x 8.00 x 6.00)

15/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

1.
2.
3.
4.
5.
6.

Housing cable adapter, 142485-01
200151 cable
Accel to Velocity ProTIM-R
TIM housing
200150 accelerometer
Machine casing

Figure 4: Housing Cable Adapter

16/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

1.
2.
3.
4.
5.
6.
7.
8.

To SPATIM housing
Accel to Velocity ProTIM-R
200151 cable200150 accelerometer
Wiring in rigid conduit
1-inch conduit body near machine
141887-02 Conduit Cable Adapter

Figure 5: Dual Conduit Cable Adapter

17/18

200200 ProTIM-R
Datasheet

163662 Rev. AK

Copyright 2021 Baker Hughes Company. All rights reserved.

Bently Nevada, Keyphasor, Trendmaster and Orbit Logo are registered trademarks of Bently Nevada, a Baker Hughes
Business, in the United States and other countries. The Baker Hughes logo is a trademark of Baker Hughes Company.
All other product and company names are trademarks of their respective holders. Use of the trademarks does not
imply any affiliation with or endorsement by the respective holders.
Baker Hughes provides this information on an “as is” basis for general information purposes. Baker Hughes does notmake any representation as to the accuracy or completeness of the information and makes no warranties of any
kind, specific, implied or oral, to the fullest extent permissible by law, including those of merchantability and fitness
for a particular purpose or use. Baker Hughes hereby disclaims any and all liability for any direct, indirect,
consequential or special damages, claims for lost profits, or third party claims arising from the use of theinformation, whether a claim is asserted in contract, tort, or otherwise. Baker Hughes reserves the right to makechanges in specifications and features shown herein, or discontinue the product described at any time without
notice or obligation. Contact your Baker Hughes representative for the most current information.
The information contained in this document is the property of Baker Hughes and its affiliates; and is subject tochange without prior notice. It is being supplied as a service to our customers and may not be altered or its content
repackaged without the express written consent of Baker Hughes. This product or associated products may becovered by one or more patents. See Bently.com/legal.

1631 Bently Parkway South, Minden, Nevada USA 89423
Phone: 1.775.782.3611 (US) or Bently.com/support
Bently.com

18/18