§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIES■ Common standard specifications● High quality/high reliability

Highly reliable electronic parts are adopted.
Aging test of each part as well as burn-in aging test of the product under a high temperature are implemented.
● PCB treatment

In order to reinforce insulation resistance stability of PCB surfaces and prevent the surfaces from insulation
deterioration, B side of the PCB was cleaned and coated with high humidity resistant varnish after parts
installation.
● Output limiter circuit

Even if an excessive input is applied, the product confines the output to about 1.5 times of rating and protects theoutput side equipments.
■ Type code designation

C

(1)

P

(1) Product (kind of conversion)
Mark
ADT
MLT
LT
FGT
AMT
VFT

(2)

(3)

―

(4)

(2) Dielectric strength voltage

Product (kind of conversion)
Adding/subtracting
Multiplying/dividing
Temperature/pressure correction
Function generating
Analog backup
Voltage pulse

Mark
1

Dielectric strength voltage(50/60Hz)AC1,500V for 1 min.
between input andoutput(5)(3) (4) (5)(3) input specification(4) output specification(5) auxiliary supply
Refer to individual
specifications.

■ Standard specification
Item

Specification

Tolerance% against output span

Effect of temperature

23±10℃ tolerance %Characteristics

In conformity with JIS C 1111-1989 in tolerance

Output ripple≦1%p-p against output span

External adjustment of output±5% adjustable

Auxiliary supply

Indicated in each specifications

Overvoltage
Over current
Insulation resistanceMaterial of outer caseAppearance color
Operating temperature/humidity range
Storage temperature range

Products List

Input

2 times (10 sec.), 1.2 times (continuity) of rated voltage

Auxiliary supply

1.5 times (10 sec.), 1.2 times (continuity) of rated voltage

10 times (5 sec.), 1, 2 times (continuity) of rated current
Between input terminal, output terminal, auxiliary supply terminal
outer case (earth) ≧50MΩ at DC500V
Fire-retardant ABS resin
Outer caseBlack (N 1.5)

Rating plate

Dark blue (5PB 2/6)

0-＋55℃, 5-90℃RH (No Condensation)-40-＋70℃

1§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIES

ADDING/SUBTRACTING TRANSDUSER
CADTP1 -■ Use
A transducer does adding and subtracting of 3 inputs. By a

CADTP1-C7H1

programming unit (CCM-1), it is possible to change a(80×50×133mm/500g)

parameter or output a simulated output for a loop test.

■ Connection diagram■ Features
1. Constant voltage/current output.
2. Withstand voltage between electric circuit and outer caseAC2, 000V (50/60Hz), AC1, 500V (50/60Hz) for 1 minutebetween input/output and auxiliary supply, or AC1, 500V
(50/60Hz) for 1 minute between input and output.
3. Plus/minus input/output is not manufacturable.
4. Impulse withstands voltage 5kV, 1.2/50µs (between electric
circuit and outer case), and positive/ negative polarity 3
times each is guaranteed.

■ Specification
Input (input resistance)
A8 : DC1-5V (approx.1MΩ)C7 : DC4-20mA (approx.100Ω)
00 : other than those above

Output (load resistance)
1 : DC0-100mV (≧200Ω)
2 : DC0-1V(≧200Ω)3 : DC0-5V(≧1kΩ)
4 : DC 0-10V(≧2kΩ)
5 : DC1-5V(≧1kΩ)
A : DC0-1mA(≧12kΩ)B : DC0-5mA(≧2.4kΩ)C : DC0-10mA (≦1.2kΩ)D : DC0-16mA (≦750Ω)E : DC1-5mA(≦3kΩ)
F : DC4-20mA (≦750Ω)H : DC4-20mA (≦800Ω)
DC1-5V (≧250kΩ)SW switching
0 : other than those above

Auxiliary supply

Common specification

1 : AC100V(+10%, -15%),50/60Hz
2 : AC110V(+10%, -15%),50/60Hz
3 : AC200V(+10%, -15%) 50/60Hz
4 : AC220V(+10%, -15%), 50/60Hz
5 : DC24V(+10%, -15%)
0 : other than those above

Tolerance (when gain is ≦1) :±0.25%
Consumption VA:
AC power source:2.5VA
DC power source:3.0W
Weight:AC power source:500g
DC power source:400g●Open of current output: even if the current output terminal is used in a state of regular open, there is no problem.
Also, a voltage of approx. 25V occurs on the output terminal.

● Operational expression
Input:

X1-X3 (0-100%)

Output:X0 (0-100%)■ Block diagram①Modular jack②Input circuit③Analog multi-flexor④CPU operational circuit⑤Pulse width demodulation circuit⑥Output circuit⑦Insulated power source circuit

Operational expression:
X0＝K0｛K1 (X1＋A1)＋K2 (X2＋A2)＋K3 (X3＋A3) ｝＋A0
Gain:

K0-K3 (±29.999)

Bias:

A0-A3 (±299.99%)● Factory preset
Products are shipped in the following setting.
(Can be changed by specification)
PARAMETER
NO.
DATA
A1
0.0%
A2
0.0%
A3
0.0%
A0
0.0%
K1
0.5
K2
0.3
K3
0.2
K0
1.0

Products List

■ Purchase specifications●Item to specify

CADTP1

Type
-

C7
Input

H

1

OutputAuxiliary
supply2§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIES

MULTIPLYING/DIVIDING TRANSDUSER
CMLTP1 -■ Use
A transducer does multiplying and dividing of 3 inputs. By

CMLTP1-C7H1

a programming unit (CCM-1), it is possible to change a(80×50×133mm/500g)

parameter or output a simulated output for a loop test.

■ Connection diagram■ Features
1. Constant voltage/current output.
2. Withstand voltage between electric circuit and outer caseAC2, 000V (50/60Hz), AC1, 500V (50/60Hz) for 1 minutebetween input/output and auxiliary supply, or AC1, 500V
(50/60Hz) for 1 minute between input and output. 3.
Plus/minus input/output is not manufacturable.
4. Impulse withstands voltage 5kV, 1.2/50µs (between electric
circuit and outer case), and positive/ negative polarity 3
times each is guaranteed.

■ Specification
Input (input resistance)
A8 : DC1-5V (approx.1MΩ)C7 : DC4-20mA (approx.100Ω)
00 : other than those above

Output (load resistance)
1 : DC0-100mV (≧200Ω)
2 : DC0-1V(≧200Ω)3 : DC0-5V(≧1kΩ)
4 : DC 0-10V(≧2kΩ)
5 : DC1-5V(≧1kΩ)
A : DC0-1mA(≧12kΩ)B : DC0-5mA(≧2.4kΩ)C : DC0-10mA (≦1.2kΩ)D : DC0-16mA (≦750Ω)E : DC1-5mA(≦3kΩ)
F : DC4-20mA (≦750Ω)H : DC4-20mA (≦800Ω)
DC1-5V (≧250kΩ)SW switching
0 : other than those above

Auxiliary supply

Common specification

1 : AC100V(+10%, -15%),50/60Hz
2 : AC110V(+10%, -15%),50/60Hz
3 : AC200V(+10%, -15%) 50/60Hz
4 : AC220V(+10%, -15%), 50/60Hz
5 : DC24V(+10%, -15%)
0 : other than those above

Tolerance (when gain is ≦1) :±0.25%(only when each input is morethan or equal to 5%)
Consumption VA:
AC power source:2.5VA
DC power source:3.0W
Weight:AC power source:500g
DC power source:400g●Open of current output: even if the current output terminal is used in a state of regular open, there is no problem.
Also, a voltage of approx. 25V occurs on the output terminal.

● Operational expression
Input:

X1-X3 (0-100%)

Output:X0 (0-100%)■ Block diagram①Modular jack②Input circuit③Analog multi-flexor④CPU operational circuit⑤Pulse width demodulation circuit⑥Output circuit⑦Insulated power source circuit

Operational
expression : X0＝K0 (K1X1+A1) (K2X2+A2) ＋A0(K3X3+A3)
Gain:

K0-K3 (±29.999)

Bias:

A0-A3 (±299.99%)● Factory preset
Products are shipped in the following setting.

■ Purchase specifications(Can be changed by specification)●Item to specify

PARAMETER
NO.
DATA
A1
0.0%
A2
0.0%
A3
0.0%
A0
0.0%
K1
1.0
K2
1.0
K3
1.0
K0
1.0

Products List

CMLTP1 -

Type
C7
Input

H

1

OutputAuxiliary
supply3§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIESTEMPERATURE/PRESSURE CORRECTING TRANSDUSER
CLTP1 -■ Use
A transducer

that

takes

in

temperature,pressureanddifferential pressure, then processes them for measurement offlow rate. By a programming unit (CCM-1), it is possible to change
a parameter or output a simulated output for a loop test.

CLTP1-C7H1(80×50×133mm/500g)■ Connection diagram■ Features
1. Constant voltage/current output.
2. Withstand voltage between electric circuit and outer case AC2,000V (50/60Hz), AC1, 500V (50/60Hz) for 1 minute between
input/output and auxiliary supply, or AC1, 500V (50/60Hz) for 1
minute between input and output.
3. Plus/minus input/output is not manufacturable.
4. Impulse withstands voltage 5kV, 1.2/50µs (between electric
circuit and outer case), and positive/ negative polarity 3 times
each is guaranteed.

■ Specification
Input (input resistance)
A8 : DC1-5V (approx.1MΩ)C7 : DC4-20mA (approx.100Ω)
00 : other than those above

Output (load resistance)
1 : DC0-100mV (≧200Ω)
2 : DC0-1V(≧200Ω)3 : DC0-5V(≧1kΩ)
4 : DC 0-10V(≧2kΩ)
5 : DC1-5V(≧1kΩ)
A : DC0-1mA(≧12kΩ)B : DC0-5mA(≧2.4kΩ)C : DC0-10mA (≦1.2kΩ)D : DC0-16mA (≦750Ω)E : DC1-5mA(≦3kΩ)
F : DC4-20mA (≦750Ω)H : DC4-20mA (≦800Ω)
DC1-5V(≧250kΩ)SW switching
0 : other than those above

Auxiliary supply

Common specification

1 : AC100V(+10%, -15%),50/60Hz
2 : AC110V(+10%, -15%),50/60Hz
3 : AC200V(+10%, -15%) 50/60Hz
4 : AC220V(+10%, -15%), 50/60Hz
5 : DC24V(+10%, -15%)
0 : other than those above

Tolerance (when gain is ≦1) :±0.25%(only when each input is morethan or equal to 5%)
Consumption VA:
AC power source:2.5VA
DC power source:3.0W
Weight:AC power source:500g
DC power source:400g●Open of current output: even if the current output terminal is used in a state of regular open, there is no problem.
Also, a voltage of approx. 25V occurs on the output terminal.

● Operational expression
X0＝K1X1

K2X2+A2
K3X3+A3or K1√X1■ Block diagram
K2X2+A2
K3X3+A3①Modular jack②Input circuit③Analog multi-flexor④CPU operational circuit⑤Pulse width demodulation circuit⑥Output circuit⑦Insulated power source circuit

X0: output signal
X1: differential pressure input signal
X2: pressure input signal
X3: temperature signal
Gain: K1-K3 (±29.999)
Bias: A2, A3 (±299.99%)● Factory preset
Products are shipped in the following setting.
(Can be changed by specification)
Without square root extracting function.
PARAMETER
NO.
DATA
A2
0.0%
A3
0.0%
K1
1.0
K2
1.0
K3
1.0

Products List

■ Purchase specifications●Item to specify

CLTP1 -

Type
C7
Input

H
Output1
Auxiliary
supplyPlease specify as [with square root extracting function] in the case of √X1.

4

§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIESFUNCTION GENERATING TRANSDUSER
CFGTP1 -■ Use
A transducer which does broken line operation of a DC input. Up
to15 broken lines (kinked point X and Y 16 each) can be changed
by a programming unit (CCM-1).

■ Features

CFGTP1-C7H1(80×50×133mm/500g)■ Connection diagram

1. Constant voltage/current output.
2. Withstand voltage between electric circuit and outer case AC2,000V (50/60Hz), AC1, 500V (50/60Hz) for 1 minute between
input/output and auxiliary supply, or AC1, 500V (50/60Hz) for 1
minute between input and output.
3. Plus/minus input/output is not manufacturable.
4. Impulse withstands voltage 5kV, 1.2/50µs (between electric
circuit and outer case), and positive/ negative polarity 3 times
each is guaranteed.

■ Specification
Input (input resistance)
A8 : DC1-5V (approx.1MΩ)C7 : DC4-20mA (approx.100Ω)
00 : other than those above

Output (load resistance)
1 : DC0-100mV (≧200Ω)
2 : DC0-1V(≧200Ω)3 : DC0-5V(≧1kΩ)
4 : DC 0-10V(≧2kΩ)
5 : DC1-5V(≧1kΩ)
A : DC0-1mA(≧12kΩ)B : DC0-5mA(≧2.4kΩ)C : DC0-10mA (≦1.2kΩ)D : DC0-16mA (≦750Ω)E : DC1-5mA(≦3kΩ)
F : DC4-20mA (≦750Ω)H : DC4-20mA (≦800Ω)
DC1-5V(≧250kΩ)SW switching
0 : other than those above

Auxiliary supply

Common specification

1 : AC100V(+10%, -15%),50/60Hz
2 : AC110V(+10%, -15%),50/60Hz
3 : AC200V(+10%, -15%) 50/60Hz
4 : AC220V(+10%, -15%), 50/60Hz
5 : DC24V(+10%, -15%)
0 : other than those above

Tolerance (when gain is ≦1) :±0.25%
Consumption VA:
AC power source:2.5VA
DC power source:3.0W
Weight:AC power source:500g
DC power source:400g●Open of current output: even if the current output terminal is used in a state of regular open, there is no problem. Also, a voltage of approx. 25V occurs on the output terminal.

● UR-1 precise resistance unit

(Selling separately)■ Block diagram

Use UR-1 combined with a transducer of voltage
input. When changing the transducer in a hot line stateat the time of current input, if measures against open
are necessary, connect UR-1 to socket and convert it
into a voltage signal before using it.
(UR-1, resistance specified)①Modular jack②Input circuit③CPU operational circuit④Pulse width demodulation circuit⑤Output circuit⑥Insulated power source circuit

X-axis: X1-X16(-15-+115%)
Y-axis: Y1-Y16(-15-+115%)■ Purchase specifications●Item to specify● Factory preset
Products are shipped in the following setting.
(Can be changed by specification)

1
2
3
4

Products List

PARAMETER
X/DATA
Y/DATA-1.00%
1-1.00%
0.00%
2
0.00%
100.00%3
100.00%110.00%4
110.00%

CFGTP1 -

Type
C7
Input

H

1

OutputAuxiliary
supplyIn the case of specifying the kinked point, only specify the number of necessary point by orderof X1＜X2＜……＜X15＜X16.

5

§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIES

ANALOG BACKUP TRANSDUSER
CAMTP1 -■ Use
A transducer which provides output with a backup whena computer or a PID controller was down. Follow-up
movement of input/output (SPEED) and output backup
function (HOLD) at the time of supporting power failure
are settable by a programming unit (type CCM-1) .
CAMTP1-C7H1■ Features
1. Constant voltage/current output. A product with aselection switch for DC4-20mA/DC1-5V ismanufacturable.
2. Withstand voltage between electric circuit and outercase AC2, 000V (50/60Hz), AC1, 500V (50/60Hz) for 1
minute between input/output and auxiliary supply.
3. With or without the output hold at the time of auxiliary
supply failure, and the response time of output follow-up
can be set or changed by the programming unit CCM-1.
Also, a simulated output for a loop test is available.
4. With setting value of the programming unit CCM-1
stored in a nonvolatile memory, there is no need to set
the CCM-1 again even if the electric power of main
device failed.
5. Manual UP/DOWN operation of the external control
input is possible.

(80×50×133mm/500g)■ Connection diagram■ Specification
Input (input resistance)
A1 : DC0-10mV (approx.1MΩ)A2 : DC0-50mV (approx.1MΩ)A3 : DC0-60mV (approx.1MΩ)A4 : DC0-100mV (approx.1MΩ)A5 : DC0-1V(approx.1MΩ)A6 : DC0-5V(approx.1MΩ)A7 : DC0-10V (approx.1MΩ)A8 : DC1-5V(approx.1MΩ)C1 : DC0-10μA*1 (100mV)C2 : DC0-100μA (100mV)
C3 : DC0-1mA (approx.100Ω)
C4 : DC0-5mA (approx.100Ω)
C5 : DC0-10mA (approx.100Ω)C6 : DC0-16mA (approx.100Ω)
C7 : DC4-20mA (approx.100Ω)
00 : other than those above

Output (load resistance)
1 : DC0-100mV (≧200Ω)
2 : DC0-1V(≧200Ω)3 : DC0-5V(≧1kΩ)
4 : DC 0-10V(≧2kΩ)
5 : DC1-5V(≧1kΩ)
A : DC0-1mA(≧12kΩ)B : DC0-5mA(≧2.4kΩ)C : DC0-10mA (≦1.2kΩ)D : DC0-16mA (≦750Ω)E : DC1-5mA(≦3kΩ)
F : DC4-20mA (≦750Ω)H : DC4-20mA (≦800Ω)
DC1-5V(≧250kΩ)SW switching
0 : other than those above

Auxiliary supply

Common specification

1 : AC100V(+10%, -15%),50/60Hz
2 : AC110V(+10%, -15%),50/60Hz
3 : AC200V(+10%, -15%) 50/60Hz
4 : AC220V(+10%, -15%), 50/60Hz
5 : DC24V(+10%, -15%)
0 : other than those above

Tolerance:±0.25% *2(% against output span)
Consumption VA:
AC power source:2.5VA
DC power source:3.0W
Weight:AC power source:500g
DC power source:400g●Open of current output: even if the current output terminal is used in a state of regular open, there is no problem.
Also, a voltage of approx. 25V occurs on the output terminal.
*1. Circuit voltage ≦15V for an input of 10µA.
*2. Tolerance becomes ±0.5% when input voltage is less than 50mV; input current is less than 100µA.

Products List

6§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIES● UR-1 precise resistance unit (Selling separately)
Use UR-1 combined with a transducer of voltage input. When changing the transducer in a hot line state at the time ofcurrent input, if measures against open are necessary, connect UR-1 to socket and convert it into a voltage signal before
using it.
(UR-1, resistance specified)
Control input
UP (a contact), DOWN (a contact), AUTO/MAN. (b contact)
Control input
DC24V, 7mA
Contact switching
Voltage Current
0-30S±1S/F.S (can be set at will by 1S step with CCM-1) Standard Factory preset: SPEED is set
Input/output
follow-up response
to 10S.
UP/DOWN follow-up
20S±1S (fixed)/F.S *response
0 Begins the reset when the electric power recovers
HOLD = 0 or 1 can be set at will by
HOLD function
CCM-1. HOLD = 0 at the time of
At the time of a power failure, it starts from the1
the standard output.
state before the failure.
Output does follow-up response to input at the time of AUTO mode.
AUTO/MAN. signal
Output does follow-up response to UP/DOWN signal at the time of MAN. mode.
*Output rises to 125% when UP continues short-circuiting from the outside.
Output drops to 0% When DOWN continues short-circuiting,.

■ Block diagram①Modular jack②Input circuit③Digital input circuit④CPU operational circuit⑤Pulse width demodulation circuit⑥Output circuit⑦Insulated power source circuit■ Purchase specifications●Item to specify

CAMTP1 -

Type
C7
Input

Products List

H

1

OutputAuxiliary
supply7§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIES

VOLTAGE PULSE TRANSDUSERCVFTP1 -■ Use
A transducer which converts a DC input signal into a unit pulse.
Please use the device by combining it with either one of open
collector, voltage pulse, relay contact and photo-MOS relay output
according to application. Also, the device has the function to cut
the output pulse at the time of a low input as standard equipment.
Setting of the frequency of output pulse, pulse width, output cut
value at the time of a low input are possible by using a
programming unit (type CCM-1).

CVFTP1-C711(80×50×133mm/500g)■ Connection diagram■ Features
1. Constant voltage/current output.
2. Withstand voltage between electric circuit and outer caseAC2, 000V (50/60Hz), AC1, 500V (50/60Hz) for 1 minute between
input/output and auxiliary supply, or AC1, 500V (50/60Hz) for 1
minute between input and output.
3. Plus/minus input/output is not manufacturable.
4. Impulse withstands voltage 5kV, 1.2/50µs between electric
circuit and outer case is guaranteed.

■ Specification
Input (input resistance)
A1 : DC0-10mV (approx.1MΩ)A2 : DC0-50mV (approx.1MΩ)A3 : DC0-60mV (approx.1MΩ)A4 : DC0-100mV (approx.1MΩ)A5 : DC0-1V(approx.1MΩ)A6 : DC0-5V(approx.1MΩ)A7 : DC0-10V (approx.1MΩ)A8 : DC1-5V(approx.1MΩ)C1 : DC0-10μA*1 (100mV)C2 : DC0-100μA (100mV)
C3 : DC0-1mA (approx.100Ω)
C4 : DC0-5mA (approx.100Ω)
C5 : DC0-10mA (approx.100Ω)C6 : DC0-16mA (approx.100Ω)
C7 : DC4-20mA (approx.100Ω)
00 : other than those above

Output (load resistance)
1 : voltage pulse
10Vp (≧2kΩ)
2 : open collector
DC48V, 100mA MAX.
3 : no-voltage 1a contact
DC30V, 200mA 5,000,000
times(resistanceload)
AC125V, 200mA 2,000,000
times (COSφ=1)
4 : Photo MOS relay
AC/DC125V, 70mA MAX.
(resistance load)*1. Circuit voltage: ≦15V for an input of 10µA.

Auxiliary supply

Common specification

1 : AC100V(+10%, -15%),50/60Hz
2 : AC110V(+10%, -15%),50/60Hz
3 : AC200V(+10%, -15%) 50/60Hz
4 : AC220V(+10%, -15%), 50/60Hz
5 : DC24V(+10%, -15%)
0 : other than those above

Tolerance:±0.25% *2(% against output span)
Consumption VA:
AC power source:2.5VA
DC power source:3.0W
Weight:AC power source:500g
DC power source:400g*2. Tolerance becomes ±0.5% when input voltage is less than 50mV; input current is less than 100µA.

Output range
Mark

Output signal (allowable load)1

Voltage pulse 10Vp (load≧2ｋΩ)

2Open collector DC48V, 100mA MAX.

3

No-voltage 1a contact

4

Photo-MOS relay AC/DC125V,
70mA MAX.

Range of output
frequency
10p/h-36,000p/h(0.002778Hz-10Hz)
3:≦3,600P/h (1Hz)● Factory preset
Products are shipped in the following setting.
(Can be changed by specification)
PARAMETER
No.
DATA
P
3,600p/h
C
1.0%
T
100ms

Mark

Name

P

Number of theoutput pulseC
T(1)Low input cut value
Output pulse width

Setting range
10P/h-36, 000P/h
However, 1a contact:
MAX.3, 600P/h
0.0-20.0%50-300ms■ Block diagram■ Purchase specifications●Item to specify

CVFTP1 ①Modular jack②Input circuit③V/F circuit

Type
C7
Input

1
Output1
Auxiliary
supply④CPU operational circuit⑤Output circuit⑥Insulated power source circuit

Products List

8§ PLUG-IN TRANSDUCER §SOFT SPEC. TYPEC SERIESPROGRAMMING UNIT
CCM-1

■ Use
The programming unit is a setter for changing the setting
values of the soft spec type transducers (C series). Besides
the data setting function, the programming unit can
output any value for a loop test.

■ Specification
Power: supplied by soft spec type transducers.
Connection: modular jackWeight: 300g

■ Dimensions (mm)■ Purchase specifications●Item to specify

Type
CCM-1

Products List

9