Mitsubishi Heavy Industries Technical Review Vol. 52 No. 1 (March 2015)
83

New Multi-split Inverter System
Building Air Conditioners (KXZ series) forOverseas Markets with Top-level Energy Efficiency
and Expanded Product Line-up

S a l e s D e pa r t m e n t , Ai r - C o n d i t i o n i n g &Refrigeration Division
M a c h i n e r y, E q u i p m e n t & I n f r a s t r u c t u r eTargeting overseas markets, Mitsubishi Heavy Industries, Ltd. (MHI) has developed theKXZ series of new multi-split inverter system building air conditioners, and has commercialized
them since June 2014. These new models exhibit excellent energy-saving capability owing toenhanced efficiency and diversified operational control, with improved basic performance and asignificantly expanded product line-up. The features and specifications of the new models areintroduced below.

|1. Product features(1)

Enhanced efficiency
In the KXZ series, the flow-path configuration of the outdoor unit heat exchanger wasreviewed. For the liquid-refrigerant distribution system, distributors were used instead of
conventional headers. As a result, the improved performance in refrigerant distribution allows
the heat exchanger to exhibit the maximum capability, thus significantly elevating efficiency.
In the compressor, concentrated winding motors*1 were installed to reduce power loss inmotor coils. A multi-discharge port system was adopted for the compressor scroll mechanism toprevent the power loss resulting from excessive compression. Thus, superior energy-saving
performance has been made possible, especially in the seasonal efficiency rating.
Consequently, compared with the previous models, the cooling efficiency (whenexpressed as EER*2) has been increased by nearly 40% and the heating efficiency (COP*3) bynearly 8% (in the case of 24-horsepower (HP) models). Based on the single-unit specifications,the standard models of the KXZ series (10 to 20 HP, with the exception of the 16 HP model)
exceed comparable models of other companies in terms of the average COP in both cooling andheating operations.*4(2) Significantly expanded product line-up
Owing to the technological developments and improvements for the combined use of
more than one outdoor unit, the number of combined outdoor units has been increased to three
from the conventional two. Accordingly, the possible maximum power output of the KXZ
series has also been increased from the previous 48 HP to 60 HP, which is the top level in theindustry. In the KXZ series, in addition to standard models, we can offer Hi-COP models withsubstantially improved EER and COP values. Also available are derivatives of standard large
connection models in which the allowable indoor-unit connection capacity has been expanded
to 200%*5 in comparison with the outdoor unit capacity. The product line-up has been increased
significantly, which enables us to serve the increasingly diversified needs of our customers.
(3) Improved basic performance
The outdoor unit retains the basic configuration of previous models, which haveestablished a solid position in the market for their robust reliability. Therefore, the outdoor unitsof the KXZ series have well-proven features (i.e., structurally-separated heat exchanger andmechanical compartments, and a control-box opening/closing mechanism with hinges), thus

Mitsubishi Heavy Industries Technical Review Vol. 52 No. 1 (March 2015)84

ensuring superior maintainability. Furthermore, the spatial requirement for installation wasreviewed based on an analysis of the airflow around the outdoor unit, and the refrigerator oil
recovery system was also improved. Such refinements have resulted in better basic air
conditioning performance, expanding the operable outside-temperature upper limit for cooling
operations to the dry-bulb temperature (DBT) of 46°C from the conventional DBT of 43°C. In
terms of installation flexibility, when the outdoor unit is placed above the indoor unit, themaximum vertical distance between these two units has been increased from 50 m to 70 m,allowing the KXZ series to be used in skyscrapers.
(4) Introduction of high capacity (wide range) compressors
We have developed high capacity inverter control technology and a refrigerator oil
separation system for use with high capacity compressors, whereby a single high capacity
compressor can suffice for outdoor units of a certain capacity (for which two compressors weretypically installed). Thus, the number of compressors and inverter circuit boards to be mounted
has been reduced. As a scroll DC inverter compressor, which is used in multi-split inverter air
conditioning systems that aren’t coupled with other compressors, our high capacity compressor
boasts one of the largest capacities in the world. Furthermore, by improving our originaltechnology for compressor capacity control, the compressor controllability when connected tosmall-capacity indoor units, an issue when using high capacity compressors for outdoor units,
was secured. The introduction of high capacity compressors can decrease the total weight of thecompressors to be installed by approximately 16 kg.
(5) MHI’s new original energy-saving control system
The KXZ series has adopted our new and original energy-saving control system (patentpending), in which the number of compressor rotations is optimized while monitoring thetemperature in the room. With this new system, the expected effect of power consumption
reduction is roughly estimated as a maximum of 34%. Other various attempts for energy
conservation were also made, including demand controllers with a three-stage power demand
control system (improved from the two-stage control system).
*1: Concentrated winding motors are installed in 10, 12, 17, 18 and 20 HP outdoor units of standard
models and standard large connection models, as well as the 8 HP outdoor unit Hi-COP model.
*2: EER stands for energy efficiency ratio, which is an indicator of performance calculated by dividing
rated cooling capacity (kW) by consumed electricity (kW). A higher EER suggests better energyefficiency.
*3: COP stands for coefficient of performance and is an indicator of performance. In the case of heating,it is calculated by dividing rated heating capacity (kW) by consumed electricity (kW). A higher COP
suggests better energy efficiency.
*4: Surveyed by MHI in November 2014 (European market models). The other companies referred tohere are the top two Japanese manufacturers in terms of market share.
*5: Among standard models, the allowable indoor-unit connection capacity is 130% in comparison withthe outdoor unit capacity.

Figure 1

EER comparison for cooling (Standard and Hi-COP models)Mitsubishi Heavy Industries Technical Review Vol. 52 No. 1 (March 2015)
85

Figure 2

Summarized mechanism of energy-saving controls|2. Product specifications
Tables 1 to 3 show the specifications of the KXZ series.
Table 1 Standard models (for a single unit)
Horsepower
Model code
Power source
Rated cooling
capacity
Capacity
Rated heating
capacityPower
consumption
Electricalfeatures

under rated
cooling condition

Powerconsumption
under rated
heating condition

10 HP

12 HP

14 HP

16 HP

17 HP

18 HP

20 HP

FDC(S)280KXZE1 FDC(S)335KXZE1 FDC(S)400KXZE1 FDC(S)450KXZE1 FDC(S)475KXZE1 FDC(S)500KXZE1 FDC(S)560KXZE1

3 phases 380-415V 50Hz/380V 60Hz

－kW

28.0

33.5

40.0

45.0

47.5

50.0

56.0

kW

31.5

37.5

45.0

50.0

53.0

56.0

63.0

kW

7.24

8.96

10.96

13.98

13.9813.97

16.62

kW

7.28

9.04

10.69

12.50

13.00

13.49

15.95

Dimensions (H x W x D)mm
1690×1350×720
2048×1350×720
Weightkg
272317370
Operating Sound PressuredB(A) 55/57
61/58
60/62
61/62
61/61
61/62
64/66
Level (cooling/heating)
Refrigerant
Type－
R410A
Connectable No. of
1-24
1-29
1-34
1-39
1-41
1-43
1-48
units
units
Indoor unit
Connectable－ P140～364 P168～435 P200～520 P225～585 P238～617 P250～650 P280～728
capacity range

Table 2 Hi-COP models (for a single unit)
Horsepower
8 HP
10 HP
12 HP
Model code
FDC224KXZXE1 FDC280KXZXE1 FDC335KXZXE1Power source－
3 phases 380-415V 50Hz/380V 60Hz
Rated cooling
kW
22.4
28.0
33.5
capacity
Capacity
Rated heating capacity
kW
25.0
31.5
37.5
Power consumption
under rated cooling
kW
4.98
6.95
8.68
condition
Electricalfeatures
Power consumption
under rated heating
kW
5.56
6.83
8.39
condition
Dimensions (H x W x D)mm
1690×1350×720
2048×1350×720
Weightkg
280
325
Operating Sound Pressure Level
dB(A)
56/57
56/56
62/57
(cooling/heating)
Refrigerant
Type－R410A
Connectable units No. of units
1-29
1-37
1-44Indoor unit Connectable capacity－P180～448
P224～560
P268～670
range

Mitsubishi Heavy Industries Technical Review Vol. 52 No. 1 (March 2015)86

Table 3Horsepower
Model code
Power source
Rated coolingcapacity
Capacity
Rated heatingcapacityPower
consumption
Electricalfeatures

under rated
cooling condition

Powerconsumption
under rated
heating condition

Standard large connection models (for a single unit)
10 HP

12 HP

14 HP

16 HP

17 HP

18 HP

20 HP

FDCL280KXZE1 FDCL335KXZE1 FDCL400KXZE1 FDCL450KXZE1 FDCL475KXZE1 FDCL500KXZE1 FDCL560KXZE13 phases 380-415V 50Hz/380V 60Hz－kW

28.0

33.5

40.0

45.0

47.5

50.0

56.0

kW

31.5

37.5

45.0

50.0

53.0

56.0

63.0

kW

7.24

8.96

10.96

13.98

13.98

13.97

16.62

kW

7.28

9.04

10.69

12.50

13.00

13.49

15.95

Dimensions (H x W x D)mm
1690×1350×720
2048×1350×720
WeightKg
280
325
378
Operating Sound PressuredB(A) 55/57
61/58
60/62
61/62
61/61
61/62
64/66
Level (cooling/heating)
Refrigerant
Type－R410A
Connectable No. of
1-37
1-44
1-53
1-60
1-50
1-53
1-59
units
units
Indoor unit
Connectable－ P140～560 P168～670 P200～800 P225～900 P238～760 P250～800 P280～896
capacity range

We have developed multi-split inverter system building air conditioners, targeting overseas
markets. The product line-up has thus been expanded significantly and these new models boast
superior energy efficiency at the top level in the industry. We will continue to develop products thatare considered to be more environmentally responsible and that satisfy the needs of our customers.