Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
2EC series-The Optimum Controller for a Heat Source Systemthat Consists of Centrifugal ChillersSATOSHI NIKAIDO*1

KENJI UEDA*2

YOSHIE TOGANO*1MINORU MATSUO*3

KOKI TATEISHI*4

For energy saving of a heat source system, sophisticating the system control matters, alongwith improving the efficiency of a heat source. Due to the complexity of advanced system control
that makes use of the performance features of a centrifugal chiller, however, challenges lie in
actually deploying it. As such, in 2010, Mitsubishi Heavy Industries, Ltd. (MHI) developed andcommercialized the heat source total control system "EC series," which comprehensively easilycontrols a heat source system. For this product, we developed advanced system control with aplain control algorithm using findings through research with a university, thereby enabling EC
series to make significant energy savings. Field verification conducted in 2012 indicates that thesystem achieved 23%-more energy saving compared with an existing cutting-edge system. Valuedfor its technical advancement and achievements, EC series was awarded the "Minister's Prize, theMinistry of Economy, Trade and Industry" for electricity conservation in the product and businessmodel category, in the "FY2013 Grand Prize for Excellence in Energy Efficiency andConservation" contest.

|1. Introduction
A centrifugal chiller is a piece of high-capacity heat source equipment mainly supplying
chilled water. It has been deployed in large-scale heat source systems such as in factories or for
district heating and cooling, not just in air conditioning systems in large buildings. Since 2003,
when we started marketing an inverter-equipped centrifugal chiller, centrifugal chillers havecontinued to enhance performance and they have now been deployed in air conditioning systems insmaller buildings and small and medium-scale factories. A heat source system consists of a main
piece of equipment, namely the centrifugal chiller, and auxiliary equipment such as a pump and acooling tower. The improved performance of a centrifugal chiller resulted in an increased share ofpower by the auxiliary equipment in the total electric power consumption of the heat source
system. Therefore, optimization of the entire system, including auxiliary equipment, has
increasingly been needed. Considering such needs from customers, EC series was developed as theoptimized system controller.
This paper presents the technical features of total heat source system optimizing controller
EC series and about field verification.

|2. Development background
Energy consumption from heat source systems including a centrifugal chiller counts forabout one third of total consumption for commercial use and therefore improvement of efficiency isexpected. MHI has pursued development and efficiency improvement of the centrifugal chiller (aninverter-equipped type in particular), which is a piece of large volume equipment, and our latest*1

Chiller & Heat Pump Engineering Department, Air-Conditioning & Refrigeration Division, Machinery, Equipment & Infrastructure*2

Deputy Director Chiller & Heat Pump Engineering Department, Air-Conditioning & Refrigeration Division,Machinery, Equipment & Infrastructure*3

Chief Staff Manager Takasago Research & Development Center, Technology & Innovation Headquarters*4

Takasago Research & Development Center, Technology & Innovation Headquarters

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
3
*1

*2

GART-I series achieved COP 25.3 as the best scores at partial load and IPLV 9.29 .
Achievement of higher performance of standalone heat source equipment appeared to benearing its limit, but there was room for further energy saving through optimization of management
measures for the entire heat source system. For example, it is expected that a 19.9% saving ofenergy is made if an inverter is equipped with a centrifugal chiller in an office building and a
24.3% saving is made by optimizing management of the number of chillers through a system
control.1 However, it requires technical knowledge and expertise to devise an optimized operational
plan that considers the performance features of an inverter-equipped centrifugal chiller and toexecute the planned operation. Therefore, a method that does not require customers withprofessional skills that a chiller manufacturer would have was expected.
Next, a heat source system is designed to cover the maximum load during the summer.
Therefore, most of the time the system operates (i.e., intermediate periods such as spring, autumn,night-time in summer) falls into the partial load area that is beyond the specification points of achiller. In addition, even during the winter, there is a cooling load in factory processes or for thepurpose of local heat supply and it is known that the operation times tend to be longer at low
cooling water temperature. "The proposition expected by our customers" involves a possible
solution for such a wide array of problems through optimized system control.
As such, we reached the belief that a heat source system operational support tool forhigh-efficient operation should be developed, while the enhancement of heat source equipment isalso necessary.
*1: COP: Coefficient of Performance. The greater the number, the higher the energy saving performance is.
*2: IPLV: Integrated Part Load Value. Based on calculation criterion of JIS B 8621 (2011)|3. Technical features
Since 2007, when there were no established methods for heat source system control that fully
exerts the capabilities of an inverter-equipped centrifugal chiller, MHI, together with a university
laboratory, has researched heat source system control through simulation. That resulted in theconclusion that significant energy saving is possible with just a plain and versatile control
algorithm. The findings and achievements were incorporated into a real controller, thus, the heatsource system total control system "EC series," which comprehensively easily controls a heatsource system, was produced. MHI put it on the market in 2010. This chapter explains the technicalfeatures with which the EC series is equipped.

3.1
(1)

Plain control algorithm to significantly save energy

Multiple chiller control for optimum load
Multiple chiller control to maintain high COP is effective in energy saving for a heatsource system. An inverter-equipped centrifugal chiller has the feature that the load area wherehigh COP is realized (hereafter “optimum load area”) is varied depending on cooling watertemperature. The performance properties of an inverter-equipped centrifugal chiller can berepresented according to the mechanical engineering principle for a general centrifugal
compressor. Based on this, the optimum load area under the current operation conditions wasderived (Figure 1). As a result, it was confirmed through simulation that electric power
consumption can be reduced by controlling the number of units based on computed results. (1)(2) Control for auxiliary equipment(Variable flow control of chilled/cooling water and cooling tower control)
Control design for auxiliary equipment in a heat source system tends to be complex. Thisis because operations of auxiliary equipment control affect the energy consumption of the otherequipment. We prepared an environment, where the annual air-conditioning loads at places likeretail facilities or office buildings can be simulated, to consider the control method. After that,
we combined a variety of heat source systems assumed from facts and data of each building
with various patterns of control methods for auxiliary equipment to understand the relation withthe electric power consumption of a system for each case. This led to the finding that control
for auxiliary equipment can be optimized with a plain algorithm using parameters that isobtainable under operation such as load value and chilled or cooling water temperature.2

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
4Figure 1

3.2

Optimum load areas of inverter-equipped centrifugal chiller

Communications interface added

The EC series is equipped with a communications interface as standard. Thanks to theinterface, it is easily connectable to auxiliary equipment and peripherals such as a centrifugal
chiller, programmable logic controller (PLC) and LAN interface (Figure 2). The communication
function is fully utilized, in particular, to communicate with MHI's centrifugal chiller. Dataobtained through communication with sensors can be used to get temperature and flow data that arenecessary in system control. This eliminates the necessity of sensors on the facility side that itotherwise should have and leads to a reduction of construction costs. Besides, specific parameters
only necessary for chillers such as the optimum load area, which is different in each model, arecomputed by the control unit on the chiller side, whereas EC series uses the results to control
auxiliary equipment or to calculate the best number of units under operation. Through this,complicated work needed to create the program for a complex characteristic curve for chillers iseliminated, which otherwise must be done if the system for optimum control is configured in thedesign of the facility. Furthermore, the capability to communicate with upstream equipment such as
PLC and LAN make monitoring from remote places easy.

Figure 2

EC series' hardware configuration

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
53.3

Standardization of embedded control program

In the case of programming for heat source system control in general, the program designer
writes codes for each case from the connection diagram for the facility onsite. However, EC series
is run by one standard control program. Control functions to be installed were narrowed down tokey functions and were incorporated in a versatile program. They include functions necessary forstable system operation (cooling water bypass valve control and chilled water bypass valve control)
as well as the ones mentioned in section 3.1 (multiple chiller control, variable flow control ofchilled/cooling water and cooling tower control). Parameters such as the necessity of a controlling
function, choice of model and the number of chillers are automatically configured based on thepreset parameters and communications with the chiller so as to accord with the customer's system
configuration.
Verification with a real unit has a limitation as many configuration patterns of heat source
systems are possible. To address this, we created a verification system using PRANET3, a provensimulation code that was used in dynamic characterization for our power plants and other facilities,
and created an environment where a number of patterns of heat source systems are configured andrepresented as a physical model on a computer. Using this system, verification of the combination
with the control logic was performed.
The standardization of the control program obtained the following results:(1) Transition from on-site integral-style programming to mass-produced-type programming,
which resulted in enhancement of product quality and reliability, as well as in cost saving
for control design.
(2) Saving of verification time for trial operation by pre-verification in our company, which cut
operating costs onsite.

3.4

High value-added functions featured

The avoidance of performance degradation of a centrifugal chiller is also important inefficiently operating a heat source system. This product can always calculate executable COP that acentrifugal chiller originally has (hereafter "target COP") and enables comparison with actually
measured COP. We expect that our customers will improve their chiller operation and early
detection of abnormalities by comparing the COP values. In fact, in the trial operation phase,approximately 30% of cases of performance degradation due to inadequate parameter tuning for achiller were detected early and improved4 (Figure 3).

Figure 3

Performance degradation detection of target/measured COP|4. Product specifications
The appearance of EC series is not particularly different to that of a general controllingboard. For a user interface, a 10.4-inch touch panel is employed. The screen layout wasergonomically designed by our design department, with consideration given to the operability andease for viewing by an operator (Figures 4, 5).

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
6The lineup is two models: EC-3 which is controllable for up to three centrifugal chillers andEC-6 for up to six, which is equivalent to a large-scale system (Table 1).

Figure 4 Appearance of EC
series EC-3

Figure 5 EC series systematic diagram on screen

Table 1
Item
Target facility
Number of chillers to control

Controlling functions

Outer dimension

WidthHeight
DepthWeight
Power source specification
Installation method

Specifications of EC series

Model: EC-3
Model: EC-6
Heat source facilities composed of centrifugal chillers andair-cooled heat pumps manufactured by MHI
1 to 3 units
1 to 6 units
Six functions for optimum control in heat source systems(2) Variable flow control of(1) Multiple chiller control
cooling water(3) Variable flow control of(4) Cooling tower control
chilled water(5) Cooling water bypass valve (6) Chilled water bypass valve
controlcontrol
700 mm
800 mm1300 mm1800 mm
350 mm
500 mmAppx. 240 kg
Appx. 130 kg
Single phase 100V-125V, 50Hz/60Hz common use(Optional: Single phase 200V class)Wall hungStanding|5. Field verification
Performance verifications by third parties (including a university) have been conducted sincefiscal 2012 at the Sony Corporation Sendai Technology Center, which introduced EC series after
facility renovations.5 The heat source system to undergo the field verification is one with two unitsof an inverter-equipped centrifugal chiller of 500USRt (1USRt=3.516kW) and all the auxiliary
equipment is equipped with an inverter (Figure 6).
In fiscal 2012, appraisal of verification data indicated a high efficiency of annual averagesystem COP 7.7*3. In fiscal 2004, it had also recorded a good result of annual average system COP
5.96 with a cutting-edge heat source system before the renovations, but this represents a further
23% energy saving. The performance gaps are particularly evident in the winter season, during
which thermal load becomes low as outside air temperatures go down. This indicates the advantageof control at low thermal load by EC series (Figure 7).
*3: This figure represents the COP of the entire heat source system; not of a chiller alone but including
auxiliary equipment.

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
7Figure 6 Systematic diagram of heat source system at Sony Corporation
Sendai Technology CenterFigure 7

Heat source system's COP at pre- and post-deployment of EC series|6. Conclusions
EC series, an energy saving tool, facilitates optimization of a heat source system that had
presented customers with technical hurdles that were difficult to overcome. The technologies andachievements introduced in this paper were highly valued and EC series was awarded the"Minister's Prize, the Ministry of Economy, Trade and Industry" for electricity conservation in theproduct and business model category, in the "FY2013 Grand Prize for Excellence in Energy
Efficiency and Conservation" contest sponsored by the Energy Conservation Center, Japan (ECCJ).
At present, (as of the end of March 2014) this product is used by a wide range of customers:
factories for semiconductors, beverages, chemicals and other areas for industrial-use purposes andhotels, retail facilities, hospitals and other facilities for commercial-use purposes.
With a system prepared to support customers who strive to address and manage their energy
saving issues, MHI not only helps customers with optimization when they introduce the system but
also provides a service through which they can view the measured data of a heat source system on
the Internet through our remote monitoring system, which we have been offering since before thedevelopment of EC series, and understand the operation status.
This product at the present stage is a controlling program that allows for application to ourlimited series of lineups, which are heat source systems comprised of the GART, AART and ETI
series centrifugal chillers and the Voxcel series air-cooled heat pumps. In the future, we willcontinue with our efforts to make it applicable to systems that include other company's centrifugal
chillers and adsorption chillers, and we intend to evolve EC series into a versatile,customer-friendly product.

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 2 (June 2014)
8References
1. K. Ueda et al., Energy Conservation Effects of Heat Source Systems for Business Use By Advanced
Centrifugal Chillers, ASHRAE Transactions 2009 (2009) p.640-653
2. K. Ueda et al., Energy Conservation Effects of Heat Source System for Business use by Advanced
Centrifugal Chillers Part3, Proceedings of SHASE（2009-4）p.115-118
3. K. Kuwabara et al., Simulation Program Using Node-Link Networks of Fluid Plants, Mitsubishi Heavy
Industries Technical Review VOL22No.6（1985）p.55-58
4. S. Nikaido et al., Study on reliable optimal operation method for heat source system by using advanced
centrifugal chiller Part1, Practical application and field test results in commercial building, Proceedings ofSHASE(2012),p.2673-2678
5. Y. Tai et al., Development of Performance Evaluation Method for Optimal Controlled Heat Source System
Part2 Analysis of Measurement Data, Proceedings of SHASE（2013）p.105-108
6. K. Kuwahara et al., Energy Saving Performance and Effective Operation Strategies of Cooling Plant
System Using an Inverter Chiller for Building Air-Conditioning Part1 – A System Performance Evaluation
Based on Actual Operation Data Analysis, Trans. SHASE No124（2007）p.11-18