Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)15

Development of Water Quality Simulator
for Thermal Power Plants

KENSUKE NISHI*1

YOSHIO KAYUMI*2

TAKAYUKI WADA*3

SENICHI TSUBAKIZAKI*4

TAKASHI OZAKI*5

NOBUMASA MATSUI*5

As a means of quickly learning operational skills for thermal power plant facilities orpassing skills to successors, operational training simulators with human machine interfaces andplant models that can recreate the same behavior as actual plants have been utilized at powerplants and training centers. Recently, however, several plants had incidents caused by abnormal
water quality, disturbing the stable supply of power. In terms of existing operational training
simulators including the products of Mitsubishi Heavy Industries, Ltd. (MHI), there is room for
improvement in training programs dealing with water quality-induced problems, and there are few
incidents of actual problems occurring. It is therefore expected that the development and use ofwater quality simulators for thermal power plants, which can provide training programs in termsof operational procedures for abnormal water quality, can prevent the serious problems resulting
from abnormalities in water quality, and shorten the duration of plant shutdown necessary forrepair and restoration. This report gives a summary of our water quality simulator for thermal
power plants, which is useful for operational training to handle abnormal water quality-inducedproblems.

|1. Introduction
In domestic thermal power plants, water treatment is conducted to prevent problems such as
corrosion in the boiler/turbine systems, scale formation and deposition and the consequent
carryover to the turbine. Recently, there have been incidents in which deteriorating water quality
due to aging facilities or insufficient operational actions to handle urgent situations including
cooling water (seawater) leaks in the condenser caused an extensive area in the boiler/turbine
systems to be affected by abnormal water quality, eventually leading to serious problems such asleakage from steam generating tubes in the boiler.
To prevent such serious problems related to water quality abnormalities, it is essential foroperators or those in charge of water quality control to understand how numerical values obtainedin the boiler/turbine systems change when there is something wrong with water quality, and havethe ability to handle the situation by conducting appropriate treatment and operational procedures atthe right time. This report introduces our water quality simulator for thermal power plants, which isuseful for training. Its installed plant model can recreate the same behavior as actual plants. The
simulator therefore can provide educational/training programs to improve operational skills at theoccurrence of abnormal water quality-induced problems, as well as the ability to detect incipientproblematic signs from the change in water quality indicators, under virtual circumstances
matching actual power plants.

*1Control Systems Deportment, Plant Engineering Division, Power Systems Division*2

Chief Staff Manager, Control Systems Deportment, Plant Engineering Division, Power Systems Division*3

Power Systems Service Business Deportment, Power Systems Service Division, Power Systems Division*4

Chief Staff Manager, Power Systems Service Business Deportment, Power Systems Service Division, Power Systems Division*5

Chief Staff Manager, Nagasaki System Engineering Deportment, Nagasaki Division, MHI Control Systems Co

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)16|2. Importance of water quality control in thermal power plants
Figure 1 shows a water/steam system used at thermal power plants. In this system, water
circulates starting as condensate, followed by boiler feedwater, boiler water (in the boiler) andsteam (in the turbine), and finally returning to condensate. When water quality is affected, its
influence extends to downstream systems such as boiler/turbine systems over time because of thewater circulation.

Figure 1

An example of water systems at thermal power plants

One frequently-caused problem is leakage from steam generating tubes in the boiler.
Figure 2 shows water-induced problems and the sites where they occur. The number of incidents inwhich the cause is contamination by impurities such as ion-exchange resins and chemicals (e.g.,hydrochloric acid) from the demineralizer is increasing, thus posing a problem for aging water
treatment facilities. There are also other water-induced or -related problems such as
flow-accelerated corrosion (FAC) and scale deposition. Controlling water quality is becoming
increasingly important.

Figure 2

Water-induced problems and occurrence sites

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)17

The connections between abnormal water quality and the causes of serious problems,
including leakage from steam generating tubes in the boiler and equipment damage, are shown in
Figure 3. Accurate interpretation of deviations from the normal water quality values during start
up/shut down operations of the plant enables the detection of incipient signs of problems and theprediction of forthcoming symptoms (e.g., equipment failure), whereby necessary treatment can beapplied at the proper timing and ultimately the occurrence of serious problems can be prevented.
We consider this as the principal duty of those in charge of water quality control.

Figure 3

Expected problems according to diagnosis results of water quality (example)|3. Status of development of operational training simulator
At present, the capability of accurately detecting signs of problems largely depends on theexperience of those in charge of plant operation or water quality control. It is therefore ameaningful challenge to establish a method for passing on their expertise and knowledge, which arefounded on their rich and valuable experience, by means of data that can be interpreted.
In 1978, based on the expertise obtained as a plant manufacturer and through our richexperience in boiler/turbine design, manufacture and operation, as well as knowledge supported byscientific evidence such as accumulated relevant data and dynamic characteristics analysis results,
we developed and installed an in-house training simulator for facility operation at an overseas
thermal power plant. Its main purpose was the education of plant operators. Since then, we haveprovided many simulators for thermal power plant operation both inside and outside Japan. Our
progress in simulation technology development is summarized in Figure 4Figure 5 shows an example of our simulation architecture used for operational training. The
simulation results are highly accurate in terms of not only the static characteristics of actual plants,
but also their dynamic characteristics. This has been enabled by adopting a method of diligently
solving plant-model characteristic formulas (physical balance, equation of motion, and heatbalance), which are formulated according to the physical equations based on our design
technologies as a plant manufacturer such as expertise in boiler heating surfaces and turbine blade
design. Figure 6 gives a comparison of simulation results to data from an actual plant: the behaviorof an actual plant (on the left) and its plant-model behavior simulated by our simulator (on theright). The realization of static and dynamic characteristics similar to actual plants in simulation has
allowed the provision of highly reliable, reproducible and flexible training programs for plant start
up/shut down procedures and responses to urgent events, such as the occurrence of something
unusual in these processes and the incidence of problems.

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)18

Figure 4

MHI progress in simulation technology development

Figure 5

Simulation architecture for our operational training simulator

Figure 6

Simulation comparison example

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)19

In order to create more realistic virtual reality, there have been requests for operational
training simulators by which plant start up/shut down procedures can be carried out using
centralized command functions equivalent to those found in actual plants, or photographs of realmachines in actual plants to be used when handling simulated problems to restore the normalcondition. Owing to improved computational performance, simulation speed can be set 10 times
faster than the normal level. Situations resulting from water treatment problems, which took a longtime until the simulation was completed, can now be reproduced easily. Detailed physical models
can also be used for situations that were virtually created as a simplified simulation, and therefore
training can now be provided under virtual circumstances that are more similar to actual plants.

|4. Outline of our water quality simulator for thermal power plants
4.1

Functions of our water quality simulator for thermal power plants

In our water quality simulator for thermal power plants, detailed physical models related towater treatment were developed and adopted by expanding the functions of conventional
operational training simulators. The simulation results are similar to actual plants. It therefore canprovide plant operators educational and training programs to improve their on-site ability to handle
problems caused by abnormal water quality or detecting, from warnings on water quality, the signs
that can lead to problems in facilities and plant systems.

4.2

Method of installation

Figure 7 illustrates the method of installation of the water quality simulator for thermalpower plants. If it is the first operational training simulator to be installed, only a small facility
including a plant model and the operator station is needed for the installation, because the simulator
specifically focuses on plant water quality. If there is an existing operational training simulator, thefunctions for water quality simulation can be added.

Figure 7

4.3

Method of installation of water quality simulator for thermal power plants

Simulation and operational training examples

Figure 8 shows the behavior of cation conductivity (mS/m) at each sampling point in thecase of seawater leakage from cooling tubes in the condenser of a once-through boiler. Cation
conductivity, which is subject to chlorine in seawater, is an important numerical value formonitoring operational conditions and leaking seawater amounts. Our water quality simulator forthermal power plants can reproduce the same behavior of cation conductivity as seen in actual
plants. Plant operators are required to interpret increased cation conductivity levels as a precursor(incipient sign) of seawater leakage and conduct appropriate procedures and treatment.

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)
20Figure 8Behavior of water quality in the case of seawater leakage (once-through boiler)

In terms of the development of this incipient sign over time, Figure 9 shows a case in whichcountermeasures (e.g., load decrease or shutdown) were taken according to the values indicated by
the salinometer of the condenser, and the seawater-contaminated area was minimized. On the otherhand, Figure 10 is a case in which no countermeasures were taken until an increase in cation
conductivity was detected in main steam, causing all the systems to be contaminated by seawater.
As shown in these figures, by visualizing and determining how the countermeasures taken
during operation and their timings can change the degree of impact and the affected area, the water
quality simulator for thermal power plants can be used as a teaching tool for operational training toassess the effectiveness of actions.

Figure 9 Contaminated area in the water/steam system caused by seawater leakage(once-through boiler) In this case, the seawater-contaminated area is minimized.

Mitsubishi Heavy Industries Technical Review Vol. 51 No. 1 (March 2014)
21

Figure 10 Contaminated area in the water/steam system caused by seawater leakage(once-through boiler) In this case, all the systems is contaminated by seawater.

|5. Conclusion
For operators or those responsible for water quality control, the required capabilities at thetime of abnormal water quality occurrence are “the detection of water quality abnormalities(signs),” “the prediction of expected symptoms (equipment failure),” and “the application ofappropriate treatment according to the abnormalities (minimizing the area to be affected).” We
have developed a water quality simulator for thermal power plants that is useful for training andskill learning.

References
1. Tsubakizaki, S. et al., Water Quality Control Technology for Thermal Power Plants (Current Situation andFuture Prospects)，Mitsubishi Heavy Industries Technical Review Vol. 50 No. 3 (2013)
2. Tsubakizaki, S., Learn from the Experts “Cycle Chemistry” Part 1, The Journal "The Thermal and Nuclear
Power", Journal Vol. 58 No. 614 (2007.11)
3. Kuroishi et al., Improvements of Operability and Controllability for Steam Power Plants -Prior Verification
by Precise Simulation-. Mitsubishi Juko Giho Vol. 40 No. 4 (2003-7)