SPEC. SHEET

Digital Deviation Indicating Controller

RC-600Model：■ ModelModelControl action

Alarm function

OutputInput

RC-6

□

ON/OFF control action

1
2

PD control action□ － □ /No alarm action

0High limit alarm

1

High limit alarm with standby

1

Low limit alarm

2

High limit alarm with standby

2

High/Low limits alarm

4

High/Low limits alarm with standby

4High/Low limit range alarm

6

Process high alarm

8

Process low alarm

9E□

H
H
H

Relay contactR

Non-contact voltage

SDC current

A

Thermocouple (K, J) (must be specified)E■ Input specificationsRated scale:

Input type

Input TypeResolution

Input Range

K0 to 400

0 to 999

1 ( )J0 to 400

0 to 999

1 ( ): Thermocouple K, J (must be specified)■ Ordering example
RC-6 2 0 -R/E 0～400

External resistance: 100or lessK
Base model
Control action : PD action
Alarm output : No alarm action
Control output : Relay contact output
Input type: Thermocouple (Fixed)
Input spec
: Type K, input range 0 to 400■ General structure
Dimensions: 48×96×115mm (W×H×D)
Weight: Approx. 280g
Mounting: FlushCase: ABS resinColor: Dark gray
Panel: Membrane sheet
Supply voltage : 100 to 240V AC 50/60Hz(Allowable voltage fluctuation
range: 85 to 264V AC)
Power consumption: Approx. 6VA

OFF indicator

LED deviation indicator

ON indicator

ALARM indicator

SV display[+100] key[+10] key[+1] key[-100] key[-10] key[-1] keyRESET key

ALARM key

■ Indication performance
Indication accuracy: Within 1 bar [Resolution 5Input sampling period: 0.25 sec( )]■ Control performance
Setting accuracy: Within 0.3% of each input span 1digit, or 2 (4 ), whichever is greater
Control action : The following control action can be selected by the DIP switch.
PD control action (with Auto-reset function)
Proportional band (P): 10 (20 )Derivative time (D): 50 sec
Proportional cycle: 3 sec (Non-contact voltage), 30sec (Relay contact)(Not available for DC current output type)
ON/OFF control action
Hysteresis: 1 (2 )Main output: Relay contact: 1c
Control capacity: 5A 250V AC (Resistive load)
2A 250V AC (Inductive load cos =0.4)
Electric life: 100,000 cycles+2
Non-contact voltage (for SSR drive): 12 0 V DC
Max. 40mA DC (short circuit protected)
DC current: 4 to 20mA DC (Resolution: 12,000) Load resistive: Max. 600

比例帯bandProportional
ONOFF△

SV設定
SVHysteresis
動作すきまONOFF
動作すきま設定
Hysteresis

SV設定
SV■ Alarm function
The alarm action point is set from thedeviation from the SV (except Process high/low alarm), and when the input goes outside thealarm setting range, the alarm output will be turned ON.
Alarm type: The following alarm types can be selected by the rotary switch.
No alarm, High limit alarm, High limit alarm with standby, Low limit alarm, Low limit alarm with standby,
High/Low limits alarm, High/Low limits alarm with standby, High/Low limit range alarm, Process high alarm,and Process low alarm
Control action : ON/OFF action Alarm hysteresis: 1 (2 )Output: Relay contact: 1c
Control capacity: 3A 250V AC (Resistive load) 1A 250V AC (Inductive load cos =0.4)
Electric life: 100,000 cycles■ Terminal arrangementTC■ Panel cutout (Scale: mm): Thermocouple input

MAIN OUTPUT : Control output
ALARM: Alarm output
Lateral close mounting(n: Number of units mounted)

SHINKO TECHNOS CO., LTD.
Tel: 81-72-727-6100
URL: https://shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp

202104 E02