EU-TYPE EXAMINATION CERTIFICATE

12Equipment or Protective systems intended for use in Potentially
Explosive Atmospheres - Directive 2014/34/EU

3EU-Type Examination Certificate No:

FM16ATEX0107X

4Equipment or protective system:(Type Reference and Name)

FLS-02EC and FLS-02EC-H2
Photoelectric Smoke Detectors

5Name of Applicant:Fenwal Controls of Japan, Ltd.

6

Address of Applicant:78232, Tobukicho,
Hachiouji-shi,
Tokyo, 192-0001
Japan
This equipment or protective system and any acceptable variation thereto is specified in the schedule tothis certificate and documents therein referred to.
FM Approvals Europe Ltd, notified body number 2809 in accordance with Article 17 of Directive
2014/34/EU of 26th February 2014, certifies that this equipment has been found to comply with theEssential Health and Safety Requirements relating to the design and construction of equipment intended
for use in potentially explosive atmospheres given in Annex II to the Directive.
The examination and test results are recorded in confidential report number:
3057977 dated 03rd June 2020

9Compliance with the Essential Health and Safety Requirements, with the exception of those identified initem 15 of the schedule to this certificate, has been assessed by compliance with the following
documents:
EN 60079-0:2012+A11:2013 and EN 60079-1:201410

If the sign ‘X’ is placed after the certificate number, it indicates that the equipment is subject to specificconditions of use specified in the schedule to this certificate.

11This EU-Type Examination certificate relates only to the design, examination and tests of the specified
equipment or protective system in accordance to the directive 2014/34/EU. Further requirements of theDirective apply to the manufacturing process and supply of this equipment or protective system. These
are not covered by this certificate.

12The marking of the equipment or protective system shall include:
FLS-02EC-a
II 2 G Ex db IIB T6 0°C ≤ Ta ≤ +50°C
FLS-02EC-H2-a
II 2 G Ex db IIB+H2 T6 0°C ≤ Ta ≤ +50°C
Digitally signed by
Richard Zammitt
Date: 2021-01-28
11:23:09
Foxit
PhantomPDF
Version: 10.0.1

Richard Zammitt
Certification Manager, FM Approvals Europe Ltd.
Issue date: 28th January 2021
THIS CERTIFICATE MAY ONLY BE REPRODUCED IN ITS ENTIRETY AND WITHOUT CHANGE
FM Approvals Europe Limited, One Georges Quay Plaza, Dublin. Ireland. D02 E440
T: +353 (0) 1761 4200 E-mail: atex@fmapprovals.com www.fmapprovals.com

F ATEX 020 (Dec/2020)

Page 1 of 3

SCHEDULE
to EU-Type Examination Certificate No. FM16ATEX0107X
13

Description of Equipment or Protective System:
FLS-02EC and FLS-02EC-H2 detect smoke using the scattered light, detecting the scattering of the lightreflected by the smoke. There are light emitter (Infrared LED) and the detector (photo-diode) inside, theformer emits the light through the lens, and the latter detects the light scattered by smoke to detect thesmoke in the hazardous area. This detector outputs include a localized LED, and relays. The installation
locations could be battery rooms, combustible engine storage facilities, chemical plants, etc. FLS-02EC
is suitable for Group IIB, while FLS-02EC-H2 is suitable for Group IIB+H2.
The construction consists of a single flameproof box, composed of a base and cover, with three M20 or½“NPT entries. The base and the cover are constructed of ADC12 Aluminium Alloy. The approximate
weight of the flame detectors is 3 kg. The construction includes internal and external ground, along witha cable tie insertion slot on the outside.
FLS-02EC and FLS-02EC-H2 are rated for 24VDC ±10%, 10 mA (standby) and 20 mA (alarm), with anambient temperature range of 0°C to +50°C.
FLS-02EC-a
a = Entries m or n
FLS-02EC-H2-a
a = Entries m or n

14

Specific Conditions of Use:
1. The FLS-02EC and FLS-02EC-H2 include flameproof joints, consult Fenwal Controls of Japan,
Ltd. if repair of the flameproof joints is necessary.
2. Consult with Fenwal Controls of Japan, Ltd. for genuine replacement cover fasteners: M6X20
hexagon bolts of A2-70 strength class SUS304 stainless steel or better are acceptable
alternatives.’

15

Essential Health and Safety Requirements:
The relevant EHSRs that have not been addressed by the standards listed in this certificate have been
identified and assessed in the confidential report identified in item 8.

16

Test and Assessment Procedure and Conditions:This EU-Type Examination Certificate is the result of testing of a sample of the product submitted, in
accordance with the provisions of the relevant specific standard(s), and assessment of supporting
documentation. It does not imply an assessment of the whole production.
Whilst this certificate may be used in support of a manufacturer’s claim for CE Marking, FM Approvals
Europe Ltd accepts no responsibility for the compliance of the equipment against all applicable Directives
in all applications.
This Certificate has been issued in accordance with FM Approvals Europe Ltd’s ATEX Certification
Scheme.

17Schedule Drawings
A list of the significant parts of the technical documentation is annexed to this certificate and a copy has
been kept by the Notified Body.
THIS CERTIFICATE MAY ONLY BE REPRODUCED IN ITS ENTIRETY AND WITHOUT CHANGE

FM Approvals Europe Limited, One Georges Quay Plaza, Dublin. Ireland. D02 E440
T: +353 (0) 1761 4200 E-mail: atex@fmapprovals.com www.fmapprovals.com

F ATEX 020 (Dec/2020)

Page 2 of 3

SCHEDULE
to EU-Type Examination Certificate No. FM16ATEX0107X
18Certificate History
Details of the supplements to this certificate are described below:
Date

Description

05th June 2020

Original Issue.

28th January 2021

Supplement 1:
Report Reference: RR226405 dated 26th January 2021.
Description of the Change: Minor documentation changes not affecting theequipment safety.

THIS CERTIFICATE MAY ONLY BE REPRODUCED IN ITS ENTIRETY AND WITHOUT CHANGE
FM Approvals Europe Limited, One Georges Quay Plaza, Dublin. Ireland. D02 E440
T: +353 (0) 1761 4200 E-mail: atex@fmapprovals.com www.fmapprovals.com

F ATEX 020 (Dec/2020)

Page 3 of 3

Blueprint ReportFenwal Controls of Japan Ltd (155974)
Class No3230

Original Project I.D.
Certificate I.D.

3057977

FM16ATEX0107X

Drawing No.

Revision Level

Drawing Title

Last Report

ES1666

10FLS-02EC(-H2)_Instrucion Manual & Technical Bulletin

3057977

K1B00012

Chamber Base

3057977

K2B0005

2

Chamber Cover

3057977

K2B0015

2

Body Base(M Thread)

3057977

K2B0016

2

Body Base(NPT Thread)

3057977

K2B0017

2

Body Cover(Support H2)3057977

K2B0018

2

Body Cover

3057977

K2B0019

1

Main Board Electrical Schematics

RR226405

K3B00672

FLS-02EC-H2 Outline Drawing

3057977

K3B0068

5

FLS-02EC-H2 Structure Drawing

3057977

K3B0069

1

Spigot Joints-1 (-H2)

3057977

K3B0070

1

Cylindrical Joints (-H2)

3057977

K3B0082

2FLS-02EC Outline Drawing

3057977

K3B0083

5.0

FLS-02EC Structure Drawing

3057977

K3B0084

1

Spigot Joints-1

3057977

K3B0085

1

Cylindrical Joints

3057977

K3B00992

Bug Screen

3057977

K3B0100

2

Chamber Protective Cover

3057977

K3B0102

11

Nameplate FLS-02EC

RR226405

K3B0103

3Wiring Diagram

3057977

K3B0171

6

Nameplate (Supprot H2)

RR226405

K4B0094

2Lens Holder Cap

3057977

K4B0095

3Lens(Rod)3057977

K4B0096

3Lens(Status Display Lamp)

3057977

K4B0097

2PD Shield Cover

3057977

K4B0098

2PD Cap

3057977

K4B0099

2LED Cap

3057977

K4B0100

2PD Cap Cover

3057977

K4B0101

2LED Cap Cover

3057977

K4B0102

2

Rod(Status Display Lamp)

3057977

K4B0104

1Harness3057977

K4B0105

2

Terminal Board Electrical Schematics

RR226405

K4B01082

Protection Plate (For Main Board)

3057977

K4B0115

1

Stopping Plug

3057977

K4B0127

2

Rubber Sheet

3057977

K4B0128

1

Shield Sheet

3057977

OL1491

4TERMINAL BOARD

3057977

OL14983IR LED BOARD

3057977

OL14993PD BOARD

3057977

OL1593

6

MAIN BOARD

RR226405

OL1613-1

3

MECHANICAL PARTS(Product)

RR226405

OL1613-2

3

MECHANICAL PARTS(Purchase)

RR226405

QL04242Calibration & Inspection specifications.pdf

RR226405

28/01/2021

Page 1 of 1