Plate Heat Exchanger
6 Mixed Gasket Materials Manual
Introduction
About this document
 In addition to this document, the Manuals for HISAKA PHEs consist of the following six documents. Read them thoroughly andunderstand the precautions regarding the safety of the equipment and its functions before handling the equipment.

1 Installation Manual, 2 Operation and Maintenance Manual, 3 Gasketting Manual, 4 Plate Cleaning Manual,
5 “Slit-In” Type Gasketting Manual, 7 Strainer Maintenance Manual.
You can also download these documents on our company website. https://www.hisaka.co.jp/english/phe/ In this manual, LX-10 is often used as an example for explanation. Please contact us if you have any questions, as the shape may
differ from the model to be maintained.
 This document is created for a person who fully understands the language it is written in. If a person, who is not able to understandthe language written herein, will handle the equipment, please provide safety instructions to the personnel/operators.
 The PHE supplied may differ from the drawings and pictures in this document depending on the optional parts if any. Also, for the
purpose of explanation, the drawings and pictures in this document may omit the details, accessories, or the like.
 Changing the contents of this document, in part or in whole, or using this document for anything other than its intended purpose isprohibited.
About gasket use
 To prevent injury and damages, do not use the gaskets other than for their intended purpose and specifications. Also, during
maintenance, follow the instructions of related documents.
About worker limitations
 PHE maintenance should be carried out by a worker who has received training in safety and danger prevention.
Work in high places should be carried out by a worker who fully understands the danger of the work and has received training insafety and danger prevention.
Export Regulations on the Equipment
 In case of export of HISAKA PHE and its component parts such as plate, gasket and so on, please follow the local law andregulations.
Disposal of the Equipment
 Do not incinerate gaskets. Incinerating gaskets releases toxic gas and is extremely dangerous.
 Any unnecessary gasket should be disposed as industrial waste in accordance with international, national, prefectural, andmunicipal regulations.
Disclaimer
 HISAKA accepts no liability for any failures in the function or performance of the equipment caused by use of any other thangenuine parts.
 HISAKA accepts no liability for any injuries or damage borne by the user, caused by use of any other than genuine parts.
 HISAKA accepts no liability for any failures in the function or performance of the equipment caused by use of this equipment in amanner that does not adhere to the procedures indicated in this manual.

Mixed Gasket Materials Manual
Table of contents
1 Safety Precautions

P1

2 Storage / Preservation

P2

3 Gasket material lineups

P2

4 Channel-Plate Gasket Installation Procedures

Please select the model you are using from the table below.

P2 to 35 D-Gasket Installation Procedures

Please select the model you are using from the table below.

P4 to 8

6 E-Gasket Installation Procedures

Please select the model you are using from the table below.

P9 to 12

7 Inquiries

P13 to 15

Type of Gasket
Channel-Plate Gasket

ModelsPage No.

UX-00,01,10,20,30,40,80,90,100,100R,110R,130,130R,160
RX-00,10,30,50,70,90, LX-00,10,20,30,40,50,50S,90,90D
SX-10,20,30,30S,41,43,71,73,80S,80M,80L,90S,90,90M,90L

P2

FX-01,10,03,05, EX-11,15,16, CX-01,10, CXW-01

D-Gasket

CX-01D, 10D

P3

YX-80,83

P3

UX-01,20,40,80,90,100,100R,110R,130,130R,160
RX-10,30,50,70,90, LX-20,30,40,50,50S,90,90D

P4

SX-10,20,30,30S,73,80S,80M,80L, FX-03,05, EX-11,15,16, CX-10,10D
UX-00,30, SX-41,43,71

P4RX-00, FX-01,10

P5

UX-10

P5

LX-00

P6

LX-10 (Only when installing PTFE)

P6

YX-80,83

P7

CX-01, CXW-01

P7

CX-01DP8

UX-90,100,100R,110R,130,130R,160, RX-10,30,50,70,90
E-Gasket

LX-20,30,40,50, 50S,90,90D, SX-10,20,30,30S,73,80S,80M,80L,90M,90L

P9

FX-03,05, CX-10,10D
UX-00,01,10,20,30,40,80
SX-41,43,71,90S,90, EX-11,15,16P9RX-00, FX-01,10

P10

LX-00

P10

LX-10

P11

LX-10 (Only when installing PTFE)

P11

YX-80

P12

YX-83

P12

1

Safety Precautions

Read through this manual carefully before use and use the PHE properly as indicated.
If you have any questions, please inquire with our company.
Precautions are categorized using the following symbols.

WARNINGCAUTION
NOTEThis symbol indicates content where mishandling could result in death or severe injury.
This symbol indicates content where mishandling could result in injury or property damage.
This symbol indicates important matters and/or useful information.

Meanings of Symbols
Indicates items that are

Indicates items that are"prohibited (something that you must NOT do)".

"mandatory (something that you must do)".

WARNINGDo NOT loosen PHE's tightening bolts/nuts except for maintenance work.

Do NOT use tightening bolts with loosened bolt heads.

The PHE could come apart if tightening bolts/nuts are loosened before installation.

If the bolt head loosens and the bolt head (nut) comes off the bolt, it could fly off at highspeed. This is dangerous and contact could cause serious injury or property damage.

Do NOT use a flange gasket for the nozzle of heat exchangers with synthetic

Do NOT incinerate gaskets.

rubber covering.
(Flange gaskets are required for nozzles with metal covering.)

Incinerating gaskets releases a toxic gas and is very dangerous.
Any unnecessary gaskets should be disposed as industrial waste in accordancewith international, national, prefectural, and municipal regulations.
For the industrial waste treatment company, use a company that has received
permission from the prefectural governor.

In general, do NOT perform pneumatic test for medium and large size PHE.

Install a protective cover on heat exchangers that handle high temperatures,

For small size PHE, do NOT perform pneumatic test at the same pressure ashigh pressure, or dangerous fluids such as strong acids or strong alkalies.

hydrostatic test pressure.

If a dangerous fluid leaks, it could cause a serious accident.

Sealing performance could be decreased and it could be a cause of leaking.

If a leak occurs during a pneumatic test using compressed air or nitrogen, it is extremely
dangerous as, in addition to the test pressure, volume expansion causes an impact.

Make sure that the operation is stopped, the internal pressure is "0", and the

In general, do NOT perform a pneumatic test in excess of 0.75 MPaG.

fluid temperature has sufficiently dropped before disassembling the PHE.

Do NOT operate in excess of the design conditions

If a fluid sprays out from the heat exchanger interior during disassembly, it could(temperature, flow rate, pressure, etc.).

cause burns or lacerations.

It may cause deformation of the heat transfer plates or leakage. Also, the required
performance may not be achieved.
Do NOT loosen the thermometer, pressure gauge, tightening bolts and nuts, orPerform gasket replacement in a well-ventilated area or area with ventilation

any other accessories during operation and when the PHE are pressurized.

equipment.

If fluid splashes from the PHE during disassembly, it may cause burns or lacerations.

The gasket dedicated adhesives "S-1" contain organic solvents. Breathing the volatile

Do NOT use tightening bolts with damage such as significant rust or cracks.

ingredients for a long time may cause symptoms such as headache, dizziness, andIf a tightening bolt breaks during operation or during disassembly, not only will thenausea. Should these symptoms occur, move somewhere with fresh air and rest, stayfragments fly off, but there is also danger of the fluid in the heat exchanger interior

calm and warm, and seek medical attention.

spraying out.

CAUTIONDo NOT touch the side of the heat exchanger element (edge of the heat

Request an expert to perform piping work, and review the assembly drawings

transfer plates).

with them beforehand to ensure that connections are properly made.

The edge of a heat transfer plate is very sharp and may cut you.

Work performed by inexperienced personnel can result in a faulty or improperBe sure to wear cut-resistant gloves whenever touching the heat transfer plates.

connection. An improper connection can result in failure to provide the specified

Do NOT place objects on the heat exchanger.

performance or an equipment malfunction.

Doing so may cause deformation of heat transfer plate or a falling object may
cause injury during operation.
Do NOT touch anything the side of the heat exchanger element (edge of the

Secure working space around the PHE.

heat transfer plates).

Installation and piping design must take into account the working space required

Deformation of the heat transfer plate may cause damage to the plate gasket andfor using disassembly and installation tools.

result in leakage.
In general, do NOT remove the stud bolts on the heat exchanger nozzles.

Clean the piping interior before connecting.

Removing the stud bolts may cause damage on the threads.

Clean piping thoroughly so that no debris enters the PHE.

If it is absolutely necessary to remove them, remove them carefully so as not todamage the screw threading on the stud bolt and the frame. Also, stud bolt removal
shall be done at the customer's liability.

Select flange gasket material that is suitable for the fluid specifications.
Flange gaskets are required for tube flange and metal boot types.

Do NOT weld or attach any piping support to the frame, guide bar, or guideInstall sufficient support for piping connected to the PHE.

bar support.

A large piping load to the PHE may cause the frame to become deformed or

Such welding may cause thermal damage to gaskets, or the attached part may

leakage.

cause interference that prevents parts from fulfilling their function. Furthermore, theinstalled part will be an obstacle and will prevent disassembly.
Do NOT allow debris or foreign material to get inside the PHE.

Perform maintenance of PHE that handle dangerous fluids, such as a strong

The clearance of the PHE is quite narrow, such that it can be easily clogged byacids or alkalies, in an environment that has wastewater treatment equipment.

debris or foreign material. When flushing the piping, take measures such as

Process waste fluid in accordance with the law and regulations. Be careful not to drain

installing a temporary strainer at the inlet piping or bypassing the PHE in order toliquid into a river or ocean area. If untreated liquid leaks, take measures in accordance

prevent debris or foreign materials from entering the PHE.

with the "Safety Data Sheet (SDS)" for the treatment liquid you used.

Do NOT allow the fluid to freeze.
In cold areas, remove the fluid inside the heat exchanger and empty the equipment
before storing it.

P1

2

Storage / Preservation

Take care following four items when storing a spare gasket long term.


Do not place any items on it to avoid gasket deformation.

Store it in a black plastic bag or cardboard box to avoid ultraviolet exposure.

Store in a cool place avoiding direct sunlight and high temperature, high humidity.



Storage lifetime of new plate gasket is 3 years after the purchase.

Take care following three items when storing a spare adhesive long term.
Store in a cool place avoiding direct sunlight and high temperature, high humidity.



Storage lifetime of new adhesive is 2 years after the purchase in case of general application “S-1” .

Mix it well before use because the solvent and solids may separate due to long-term storage.

3

Gasket material lineups

We have lineups of the following materials for gaskets.
NBR, EPDM, Silicon, FPM, PTFE encapsulated, and so on
Check the gasket material described in the "Delivery Specifications" and "Element Configuration Diagram", and then select thecorrect gasket material.
In this manual, the A-side gasket material is referred to as "MATL A" and the B-side gasket material is referred to as "MATL B".

4

Channel-Plate Gasket Installation Procedures

Models:

UX-00,01,10,20,30,40,80,90,100,100R,110R,130,130R,160, RX-00,10,30,50,70,90
LX-00,10,20,30,40,50,50S,90,90D, SX-10,20,30,30S,41,43,71,73,80S,80M,80L,90S,90,90M,90L
FX-01,10,03,05, EX-11,15,16, CX-01,10, CXW-01
Preparation

Setting
B-plateA-plateMaterial A

Material B

Material A

Material B

Material B

Material A

Material A

Material B

Cut off the port hole section and the heat transfer section for

Switch the Material A and Material B of port hole section andthe channel gaskets of Material A and Material B.

heat transfer section, and set the gasket on the heat transfer
plate. For a slit-in type, set the plate gasket using the slit, andfor an adhesive type, set the plate gasket using specified
adhesive.

P2

Models：

CX-01D, 10D
Preparation

Setting
B‐plateA‐plateMaterial B
Material A

Material B

Material A

Material B

Material A

Material A

Material B

Cut off the port hole section and the heat transfer section for

Switch the Material A and Material B of port hole section andthe channel gaskets of Material A and Material B.

heat transfer section, and set the gasket on the heat transfer
plate. slit-in type is not included in our lineup, therefore set theplate gasket using specified adhesive.

Models：

YX-80,83
V PLATE GASKET（B‐plate）

Material A

Material B

Material A

L PLATE GASKET（A‐plate）

Material B

Material A

Material B

Prepare channel gasket of Material A and Material B. Switch the Material A and Material B of port hole section and heat transfer
section, and set the gasket on the heat transfer plate. slit-in type is not included in our lineup, therefore set the plate gasket using
specified adhesive.

P3

D-Gasket Installation Procedures

5

Models：UX-01,20,40,80,90,100,100R,110R,130,130R,160, RX-10,30,50,70,90
LX-10,20,30,40,50,50S,90,90D

SX-10,20,30,30S,73,80S,80M,80L,90S,90,90M,90L,

FX-03,05,

EX-11,15,16,

CX-10,10D
Setting
Material B

Material B

H

H

H

H

Material A

Material A
H:Hole (passage hole)

Combine the DA, DB or D gaskets of Material A and Material B, and together with S distance, set them to the heat transfer plateusing the specified adhesive. For large plates or high-pressure applications, also attach the T distance.
For details, refer to "3 Gasketting Manual" for each model.
NOTE
1. Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.D-gasket of SX-20,SX-73 cut channel gasket. For details, refer to "3 Gasketting Manual" for each model.
3.For SX-80,UX-90,UX-100,UX-130 series, P distance is required. For details, refer to "3 Gasketting Manual" for each model.

Models：

UX-00,30, SX-41,43,71
Preparation-No.1

Preparation-No.2

Setting

H

Material B

Material A

Material B

Material A

H

Material B

Material A

H

H
H:Hole (passage hole)

Cut the channel gaskets of Material A

Combine the Material A and Material B

When setting gasket to the port holeand Material B in the center.

port hole sections, and cut off the slit

section without slit section of the heat

Only use the side with the port holes.

sections which shall not be used fortransfer plate, (right side in the figure

setting to the heat transfer plate (rightabove) use the specified adhesive.

side in the figure above).
NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.

P4

Models：

RX-00, FX-01,10
Preparation

Setting

H

H

Material B

Material B

Material A

Material A

H

H
H:Hole (passage hole)

Cut the D and E gaskets of Material A and Material B

Switch the Material A and Material B port holes section, and set

in the center.

to the heat transfer plate.

NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.

Models：

UX-10
Preparation

Setting

H

Material B

H

Material B

Material A

H

H
H:Hole (passage hole)

Cut the channel gaskets of Material A and Material B in the center. Use

Combine DB gaskets of Material A and Material B, andport hole side and the straight section.

together with S distance, set them to the heat transfer
plate using the specified adhesive.

NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.

P5

Models：

LX-00
Preparation

Setting
Material B

Material B

H

H

H

H

Material A

Material A

Material B

Material A
H:Hole (passage hole)

Cut D-A gasket and D-B gasket of Material A and Material B

Combine D-A and D-B gaskets of Material A and Material B,

in the center.

and together with the S distance, set them to the heat transfer
plate using specified adhesive.

NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.

Models：

LX-10（Only when installing PTFE）
Setting

H

H

PTFE

H

H

PTFE

‐encapsulated‐encapsulated

H:Hole (passage hole)
Even when sticking the material separately, the D plate sticks PTFE -encapsulated on both sides. PTFE-encapsulated D-A andD-B gaskets, and together with S distance and T distance, set them to the heat transfer plate using the specified adhesive.

NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.
3.If the plate with port hole, a spacer of t 2 mm (only the same part as frame is perforated) is required between the D plate andthe frame.

P6

Models：

YX-80

Material B

Material A

YX-83

H

H

H

H

Material A

Material B

Material B

Material A

H

H

H

H

H:Hole (passage hole)
Prepare channel gaskets of Material A and Material B.

Material A

Material B

H:Hole (passage hole)
Combine channel gaskets of Material A and Material B, andtogether with S distance, set them to the heat transfer plateusing the specified adhesive.

NOTE
1.D-plate of YX-80,YX-83 is only B-plate(Vaper side).
2.For details, refer to "3 Gasketting Manual" for each model.

Models：CX-01, CXW-01
Preparation

Setting

H

Material B

Material A

H

Material B

Material A

H

H
H:Hole (passage hole)

Cut the channel gaskets of Material A and Material B in the center.

Combine the Material A and Material B port hole sections, and set

Cut off the slit sections which shall not be used for setting to thegasket using specified adhesive.

heat transfer plate (left side in the figure above).
NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.

P7

Models：

CX-01D
Preparation

Setting

Material B

Material B

H

H

H

H

Material A

Material A

Material A

Material B
H:Hole (passage hole)

Cut the channel gaskets of Material A and Material B in the natural

Combine the Material A and Material B port hole sections, and set

centerline.

gasket using specified adhesive.

Cut off the protrusion of periphery and double seal part.
NOTE
1.Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to "3 Gasketting Manual" for each model.

P8

6

E-Gasket Installation Procedures

Models：

UX-90,100,100R,110R,130,130R,160, RX-10,30,50,70,90
LX-20,30,40,50,50S,90,90D SX-10,20,30,30S,73,80S,80M,80L,90M,90L, FX-03,05, CX-10,10D
Setting（E-plate back side）
Material B

Material B

H

H

H

H

Material A

Material A
H:Hole (passage hole)

Combine DA, DB or D gaskets of Material A and Material B, and together with S distance, set them to the heat transfer plate using
the specified adhesive. For large plates or high-pressure applications, set T distance.

NOTE
1. Above figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.D-gasket of SX-73 cut channel gasket. For details, refer to "3 Gasketting Manual" for each model.
3. Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.
4.For SX-80,UX-90,UX-100,UX-130 series, P distance is required. For details, refer to "3 Gasketting Manual" for each model.

Models：

UX-00,01,10,20,30,40,80
SX-41,43,71,90S,90, EX-11,15,16
Setting（Nozzle groove on E-frame）
Material B

H

H

H

H

Material B

Material A

Material A
H:Hole (passage hole)

Combine E nozzle gaskets of Material A and Material B and set them to the nozzle groove on E-frame.

NOTE
1.For details, refer to "3 Gasketting Manual" for each model.
2.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.
3.E nozzle gasket shall not to be set to the back side of E-plate but shall be set to the nozzle groove of E-frame.

P9

Models：

RX-00, FX-01,10
Preparation

Setting（E-plate back side）

H

Material B

Material A

H

Material B

Material A

H

H
H:Hole (passage hole)

Cut the D-plate gaskets of Material A and Material B

Switch Material A and Material B port hole sections, and set toin the center.

the heat transfer plate.

NOTE
1.For details, refer to "3 Gasketting Manual" for each model.
2.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.

Models：

LX-00
Preparation

Setting（E-plate back side）
Material B

Material B

H

H

H

H

Material A

Material A

Material B

Material A
H:Hole (passage hole)

Cut a D-A gasket and D-B gasket of Material A and Material B

Combine D-A and D-B gaskets of Material A and Material B,

in the center.

and together with S distance, set them to the heat transfer plateusing the specified adhesive.

NOTE
1.Above E-plate figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
2.For details, refer to each model's appendix, "3 Gasketting Manual."
3.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.

P10

Models：

LX-10
Setting（E-plate back side）
NBR

Material B

B

B

H

H

NBR

Material A
H:Hole (passage hole)

B:Blind

Combine DA and DB gaskets of Material A and Material B, and together with S distance, set them to the heat transfer plate using
the specified adhesive. For large plates or high-pressure applications, set T distance.
NOTE
1.LX-10A E-plate upper port holes (E1 and E2) must be closed for all products.
2.Above E-plate figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
3.For details, refer to each model's appendix, "3 Gasketting Manual."
4.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.

Models：

LX-10（Only for PTFE-encapsulated gasket）
Setting（E-plate back side）
NBR

B

B

H

H

NBR

PTFE
‐encapsulated
H:Hole (passage hole)

B:Blind

Combine PTFE-encapsulated and NBR DA gaskets, and together with S distance and T distance, set them to the heat transfer
plate using the specified adhesive.

NOTE
1.LX-10A E-plate upper port holes (E1 and E2) must be closed for all products.
2.Above E-plate figure is sample of setting of A-plate. In case of B-plate, move the plate upside-down.
3.For details, refer to each model's appendix, "3 Gasketting Manual."
4.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.
5.If the plate with port hole, a spacer of t 2 mm (only the same part as frame is perforated) is required between the D plate andthe frame.

P11

Models：

YX-80
Setting （In case of E-plate contact with port hole opened E-frame）
NBR

Material B

B

H

H

B

Material B

NBR
H:Hole (passage hole)

B:Blind

H:Hole (passage hole)

B:BlindSet E nozzle gasket(V) of Material B to E-frame.
Set B distance to E-plate back side.
Liquid-side E2 and E3 nozzles must be closed for all products.

NOTE
1.E-plate of YX-80 is only A-plate(Liquid-saide).
2.For details, refer to each model's appendix, "3 Gasketting Manual."
3.For B distance, use generic synthetic rubber (NBR).
4.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.

Models：

YX-83
Setting （In case of E-plate contact with port hole opened E-frame）

Material A
NBR

B

Material B

Material B

H

H

B

NBR
Material A

Set DA gasket of Material A, B distance and S distance to E-plate back side.
Set EB1 and EB2 gasket of Material B to E-plate back side.
Liquid-side E2 and E3 nozzles must be closed for all products.

NOTE
1.E-plate of YX-83 is only A-plate(Liquid-saide).
2.For details, refer to each model's appendix, "3 Gasketting Manual."
3.For B distance, use generic synthetic rubber (NBR).
4.Set channel gasket to the front side of E-plate. For details, refer to Chapter 4.

P12

7

Inquiries
Contact info for inquiries
HISAKA WORKS, LTD., Heat Exchanger Div., Sales Department
Osaka: 2-1-48, Higashi-Konoike-cho, Higashi-Osaka, Osaka, 578-0973, Japan

Tel : +81-(0)72-966-9601
Fax : +81-(0)72-966-8923

Tokyo: KYOBASHI OM BLDG. 1-19-8, Kyobashi, Chuo-Ku, Tokyo, 104-0031, Japan

Tel : +81-(0)3-5250-0760
Fax : +81-(0)3-3562-2759

Nagoya: Fujifilm Nagoya Bldg. 12th Floor, 1-12-17, Sakae, Naka-Ku, Nagoya,
Aichi 460-0008, Japan
Hokkaido: Sapporo Shiraishi Daiichi Seimei Bldg. 6-1-20, Higashi Sapporo 3jo,
Shiraishi-Ku, Sapporo, Hokkaido 003-0003, Japan
Onomichi: 14-15, Nishigosho-cho, Onomichi, Hiroshima, 722-0037, Japan

Tel : +81-(0)52-217-2491
Fax : +81-(0)52-217-2494
Tel : +81-(0)11-868-8010
Fax : +81-(0)11-868-8011
Tel : +81-848-21-2750
Fax : +81-848-21-2751

URL : http://www.hisaka.co.jp/english/

Global Network
HISAKAWORKS S.E.A. SDN. BHD. (MALAYSIA)
No.2, Jalan TP2. Taman Perindustrian SIME UEP, 47600 Subang Jaya, Selangor,

Tel : +60-3-8081-4185

Malaysia
E-mail : heatexc@hisaka-asia.com

Fax : +60-3-8081-7185

HISAKAWORKS S.E.A. SDN. BHD. PENANG BRANCH (MALAYSIA)No 2680, 2nd Floor, Jalan Chain Ferry, Taman Inderawasih, 13600 Perai, Penang,
Malaysia

Tel : +60-16-203-2527
Fax : +60-4-390-8588

E-mail : cyyap@hisaka-asia.com

HISAKAWORKS S.E.A. SDN. BHD. JOHOR BRANCH (MALAYSIA)
30-02, JalanMolek 1/10, Taman Molek, 81100 Johor Bahru, Johor, Malaysia

Tel : +60-16-228-4209

E-mail : cswong@hisaka-asia.com

HISAKA WORKS（THAILAND）CO., LTD. (THAILAND)
12th Floor, 825 PhairojKijja Tower, Debaratana Road, Bangna-Nua, Bangna, Bangkok

Tel : +66-2-744-3287

10260, Thailand
E-mail : heatexc@hisaka-thai.com

Fax : +66-2-744-3286

HISAKA WORKS（THAILAND）CO., LTD. SATTAHIP SALES OFFICE (THAILAND)
222/28, Moo.10, Eastiny Park 5 Village, Bang Saray, Sattahip, Chonburi 20250, Thailand

Tel : +66-3-819-9819

E-mail : heatexc@hisaka-thai.com

Fax : +66-3-819-9820

HISAKAWORKS SINGAPORE PTE LTD. (SINGAPORE)
No.18, Boon Lay Way, #02-118, Trade Hub 21, Singapore 609966

Tel : +65-6-897-8489

E-mail : heatex@hisaka-sing.com

Fax : +65-6-686-4579

PT.HISAKA WORKS INDONESIA (INDONESIA)
Ruko Grand Aries Niaga, Jalan Taman Aries Blok E1 No.3H, Jakarta Barat, Jakarta

Tel : +62-21-2931-9235

11620, Indonesia
E-mail : hisakindo@hisaka-asia.com

Fax : +62-21-2931-9235

P13

HISAPINO Manila Representative Office (PHILIPPINES)
20th Floor, One Global Place, Office Business Center, 5th Avenue & 25th Street,

Tel : +63-2-224-4129

Bonifacio Global City, Taguig 1632, Philippines

Fax : +63-2-224-4130

E-mail : hisapino@hisaka-asia.com

HISAVINA Ho Chi Minh Representative Office (VIETNAM)
4th Floor, Hoang Dan Building, 47-49, Hoang Sa Street, Da Kao Ward, District 1, Ho Chi

Tel : +84- 8-3910-7355

Minh City, Vietnam

Fax : +84-8-3910-7356

E-mail : hisavina@hisaka-asia.com

HISAVINA Hanoi Representative Office (VIETNAM)
8th Floor, Sannam Building, Duy Tan Street, Dich Vong Hau Ward, Cau Giay District,

Tel : +84-4-3795-9900

Hanoi, Vietnam

Fax : +84-4-3795-9911

HISAKA WORKS（CHINA）CO., LTD. (CHINA)
No.117 Xiangyuan Road, Changshu National New & Hi-tech Industrial Development

Tel : +86-512-5213-3000

Zone, Changshu City, Jiangsu Province 215542, P.R. China

Fax : +86-512-5213-3008

HISAKA WORKS（CHINA）CO., LTD. SHANGHAI BRANCH (CHINA)
Room 1603, Shanghai Oriental Center, 699 West Nanjing Road,

Tel : +86-21-5211-0701

Shanghai 200041, P.R. China

Fax : +86-21-5211-0720

E-mail : hisaka-sha@hisaka.co.jp

HISAKA WORKS（CHINA）CO., LTD. GUANGZHOU BRANCH (CHINA)
Room 1208, R&F Tianhe Commercial Building No.4 Huanting Road,

Tel : +86-20-3810-5515

Tianhe District, Guangzhou 5106t10,P.R. China

Fax : +86-20-3847-7539

HISAKA MIDDLE EAST CO., LTD.
P.O. Box 7102, Building No.3861, Al Khudhariya Industrial Area, Dammam 32435,

Tel : +966-13-838-4700

Kingdom of Saudi Arabia

Fax : +966-13-838-5800

Email : info@hisaka-me.com
URL : www.hisaka-me.com

HISAKA KOREA CO., LTD.
15th Floor, Gwanghwamun Building, 149 Sejong-daero, Jongno-gu, Seoul 03186, SouthTel : +82-2-739-8861/2/3

Korea
Email : heatexc@hisakakorea.com

Fax : +82-2-739-8864

HISAKA KOREA CO., LTD. BUSAN BRANCH
13th Floor, Kyowon Building, 216 Jungang-daero, Dong-gu, Busan 48733, South Korea

Tel : +82-51-747-0265
Fax : +82-51-747-0266

P14

[NOTE]

Please inform us the "MFG. Number" and "Model" described on the nameplate or Plate
Arrangement Drawing and Assembly Drawing.

For more information
Hisaka Works, Ltd. official homepage. (https://www.hisaka.co.jp/english/phe/)

Customer's memo
Please fill in the table below with PHE information.
Item Number
MFG. Number
Model
Qty
Date MFG.
Maintenancerecords
Memo

P15

Hisaka Works, Ltd., Heat Exchanger Division acquires both ISO9001 and ISO14001 certification.

HE-ME003800R5