Manuals+ — User Manuals Simpliﬁed.

FieldMate R3.04 Mobile Device Management Tool Instruction
ManualHome » FieldMate » FieldMate R3.04 Mobile Device Management Tool Instruction Manual

User’s Manual
FieldMate R3.04
Operational Precaution
IM 01R01A01-91E

Contents
1 R3.04 Mobile Device ManagementTool
2 Caution
3 Important
4 Restriction
5 Revision Information
6 Documents / Resources
7 Related Posts

R3.04 Mobile Device Management Tool
PART AThis document supplements information regarding Operational Precaution before use on IM 01R01A01-01E.
OPERATE THE PRODUCT CAREFULLY BASED ON THE FOLLOWING CAUTION, IMPORTANT, NOTES, AND
RESTRICTIONS.

Caution
Modem (F9197UF)
The modem connection is applied in non-hazardous areas only.
And the modem should not be connected to cables with over 75VDC/50VAC.
EMC Conformity Standards
CE
EN61326-1 Class A, Table1
RoHS directive: EN IEC 63000
KC MarkRegistration No: MSIP-REM-YHQ-EEN441
RCM
EN61326-1 Class A, Table1
EACH
TP TC 020/2011
WEEK
Waste Electrical and Electronic Equipment (WEEE), Directive(This directive is only valid in the EU.)
This product complies with the WEEE Directive marking requirement.
The following marking indicates that you must not discard this electrical/electronic product in domestic
household waste.
Product Category
With reference to the equipment types in the WEEE directive, this product is classiﬁed as a “Monitoring andcontrol instrument”.
Do not dispose of this product in domestic household waste.
When disposing of products in the EU, contact your local Yokogawa Europe B. V. oﬃce.

Manufacturer
Yokogawa Electric Corporation (2-9-32 Nakacho, Musashino-shi, Tokyo 180-8750, Japan)
Authorized Representative in the EEA
Yokogawa Europe BV. (Address: Euroweg 2, 3825 HD Amersfoort, The Netherlands) is the Authorized
Representative of Yokogawa Electric Corporation for this Product in the EEA.

ImportantConnection
The FieldMate should not be connected to the terminal box or the ﬁeld devices when the control system is inoperation. (i.e. CENTUM system or other venders’ control system)
USB FieldMate Modem
Analog output may change temporally in connecting with USB FieldMate Modem due to an Initial current
ﬂowing to it. Also, the communication signal is superimposed on the analog output signal.
It is recommended to set a low-pass ﬁlter (approximately 0.1s) to the receiver in order to reduce the output
eﬀect from the communication signal and to prevent the communication signal from aﬀecting the upper system.
Before online communication, conﬁrm that the communication signal does not give an eﬀect on the uppersystem.
FieldMate Installation
If the operating system of the computer into which FieldMate is to be installed is Windows 10, the Microsoft.NET Framework 3.5 function must be enabled.
Please verify as follows: Control panel – Programs – Turn Windows features on or oﬀ – “.NET
Framework 3.5 (including .NET 2.0 and 3.0)”.

1. Enabling Microsoft .NET Framework 3.5 function in advance “PC’s connection to the Internet” is necessary.
2. Enabling Microsoft .NET Framework 3.5 function during installation of FieldMate “PC’s connection to theInternet” is necessary.
• If Microsoft .NET Framework 3.5 function is not enabled, Type A Yokogawa DTM Device (described hereafter)
cannot be used as a function restriction.
Note
Installer & Generala) Software Install
PRM and FSA210 cannot coexist in the same PC.
b) Communication Interface Driver
FieldMate installer covers the followings:
USB FieldMate Modem driver
Install separately according to their instructions for other communication interface drivers.
c) Network Environment
PC with Microsoft Network Client and Internet Protocol (TCP/IP) is required for proper installationd) Stand-by Mode, Power Saving Mode on PC
d-1. Stand-by Mode on PC

It is not advisable to use the PC standby mode. After recovery, NI-FBUS may not respond.
When Ir-adaptor is used, a PC reboot may be required.
d-2. Power Saving Mode on PC
Please do not set the power management settings into power-saving mode on the communication port. In thepower-saving mode, it may not work properly.
e) Windows UserLog on to Windows with “Administrator” privileges, then or to start and operate FieldMate.
f) Handling of 3rd party DD and DTM
Although 3rd party DD and DTM are included in the Device Files DVD-ROM, Yokogawa certiﬁes the quality andoperability of only our DD and DTM.
g) Installation of Device Files on the former version
In the case of Device Files R3.09 on FieldMate R3.03.10 or earlier and PRM R4.01 or an earlier version, DTM
may not work. Please use Device Files R3.09 on FieldMate R3.04.
h) Default password for Administrator
When a new user is assigned in User Management and logs on to Windows as DefaultUser or Administrator,requires the case sensitive password, “FieldMate”.
i) BRAIN DTM Install
When individually BRAIN DTM is installed, message windows may show up during installation.
Either pressing “Yes” or “No”, the installation will be processed normally.
j) CD/DVD-ROM installer
If the installation does not start automatically, double-click the following ﬁles.
FieldMate CD-ROM\FM\Setup.exe
Device ﬁles DVD-ROM\PRMFMDeviceFiles.exe *1*1 This is eﬀective only when FieldMate is installed on your PC.
k) Adobe Reader
Adobe Reader of Adobe Systems Incorporated is required to view the user’s manual. If Adobe If the reader is notinstalled on the PC to be used, please download it from the home page of Adobe Systems Incorporated.
FOUNDATION Fieldbus H1 Communicationa) NI-FBUS Setting
Using the FOUNDATION Fieldbus H1 communication function, deﬁne the NI-FBUS before use as follows.
Device Address = Visitor
Device Type = Link Master: (“Basic” to be speciﬁed when the other Host exists)
Usage = NI-FBUSb) Device Class Setting
The device may not appear on the Segment Viewer immediately after changing the FOUNDATION Fieldbus H1
device class on Device Class Setting. It will take approximately 30 seconds to update the display.
DTM Worksa) DTM License
Some device DTM and COMM DTM specify the relevant Frame Application where they can perform with thecheck function built in.

Restriction
Installer & Generala) Device Tag Name
The table below is restrictions on the displays of Segment Viewer and Parameter Manager of the FieldMate.

Characters to pay attention

Tag Name on Segment Viewer and Parameter Manager FramePeriod [.]Only former pads before “.” is displayed. Ex.: PT12.34 -> PT12

Exclamation mark [!]Only former pads before “!” is displayed. Ex.: P112!34 -> PT12Space [SP]

Only former pads before Space is displayed. Ex.: PT12 34 -> PT12

Double quotation [“]A double quotation will be transformed to ” ” Underscore.
Ex.: PT12″34 -> PT12 34

The last character is backslash [\]The backslash is located on the Last character of the device tag, it will betransformed to ” ” Underscore. Ex. : P11234\ –>P11234

Modem and interface carda) Interface hardwareIt is not advisable to disconnect while communication is established. It may cause damage to the communication
driver, FieldMate software, etc.
Any of the followings:
HART Modem: HART communication
FieldMate Modem: BRAIN/HART communication
NI-FBUS card/NI-USB 8486: FOUNDATION Fieldbus H1 communication
PROFIusb: PROFIBUS communication
PBproUSB: PROFIBUS communication
Infrared adaptor (ACT-IR224UN-LN96-LE): ISA100.11a OOB infrared communication
FOUNDATION Fieldbus H1 Communicationa) Parameter with date and time
Data and time data may diﬀer on Parameter Manager and DTMMain Windowsa) Tag/Address Assignment of Extended Device Tag
In Message mode, after entering the New HART Message, “HART Command Error – Device is busy” may appear.
Update Segment Viewer to display the correct Device Tag.
DTM Worksa) Disconnect Operation in DTM
When the Disconnect command is activated while FieldMate is in communication with the ﬁeld device, DTM
Works may not be able to close. Terminate DTM works application on Windows task manager.
b) DTM parameter refresh
More time may be anticipated than the setting value of the refresh rate on the screen.
c) PROFIBUS DTM
Only one PROFIBUS device DTM can start from Segment Viewer due to comm DTM or driver constraint.
d) Message from PROFIBUS DTM
Block names of work and operations implemented on DTM works are not shown in History.
e) PROFIBUS DTM help window
If the parameter cannot be accessed after opening the online help window by clicking the “?” icon on the screen,open another window by selecting the menu tree, and try to access the parameter again.
f) PROFIBUS DTM for AXF
It is advisable to use PROFIBUS COMM DTM, PROFIusb DPV1 V5.45, or later.
g) PROFIBUS DTMClicking the default setting button on the left bottom corner in the oﬄine parameter window may cause acommunication error. In this case, restart DTM Works.
h) HART DTM· Clicking the refresh icon in disconnect status may cause a communication error. In this case, restart DTMWorks.
· Do not press the F1 key while the method is performed in DTM.

DD Menua) Historical Message
On DD Menu, history is saved in the form of a “block tag name” for the FOUNDATION Fieldbus H1 device.
In contrast, on Parameter Manager, it is saved in the form of a “general block tag name”, which indicates the typeand number of the block.
Device Viewera) Polling address update
While Device Viewer is open, changing the polling address, the relevant display is not updated.
Close Device Viewer, update at Segment Viewer, and start Device Viewer again.
b) Engineering unit update
While Device Viewer is open, changing the engineering unit, the relevant display is not updated.
Close Device Viewer, start Parameter Manager, and start Device Viewer again.
c) Alarm description language
The alarm description in the Device Viewer display appears in English.

Revision Information
Title: FieldMate R3.04 Operational Precaution
Manual No. : IM 01R01A01-91E
Nov. 2006/2nd Edition
Contents revised for FieldMate R1.02.10
Nov. 2008/3rd Edition
Contents revised for FieldMate R1.03.00
Aug. 2008/4th Edition
Contents added and revised on DTM2008-2 issueJan. 2009/5th Edition
Contents revised for FieldMate R2.01.00
Apr. 2009/6th Edition
Contents revised for FieldMate R2.01.10
June 2010/7th Edition
Contents revised for FieldMate R2.02.00
Feb. 2011/8th Edition
Contents revised for FieldMate R2.03.00
Sep. 2011/9th Edition
Contents revised for FieldMate R2.04.00
Aug. 2012/10th Edition
Contents revised for FieldMate R2.05.00
May 2013/11th Edition
Contents revised for FieldMate R2.06.00
Oct. 2014/12th Edition
Contents revised for FieldMate R3.01.10
Apr. 2016/13th Edition
Contents revised for standard compliant
Aug. 2016/14th Edition
Contents revised for FieldMate R3.02.00
Aug. 2017/15th Edition
Contents revised for FieldMate R3.03.00
Dec. 2017/16th Edition
Contents revised for new USB FieldMate modem (F9197UF)
Nov. 2018/17th Edition
Contents revised for FieldMate R3.04.00
June 2021/18th Edition
Contents revised on EMC Conformity Standards

IM 01R01A01-91E 18th Edition: June 18, 2021-00

Documents / Resources

FieldMate R3.04 Mobile Device Management Tool [pdf] Instruction Manual
R3.04, Mobile Device Management Tool, R3.04 Mobile Device Management Tool, Device Mana
gement Tool, Management Tool

Manuals+,