JCM Project Experience in Indonesia

Ebara Refrigeration Equipment & Systems Co., Ltd& PT. Ebara Indonesia(PTEI)JCM Project in Indonesia
EBARA has installed high efficiency chillers following three (3)Textile projects in Indonesia for humidity & temperature control.
 Title: Energy Saving for Air-conditioning and Process Coolingat Textile Factory (Two Projects)
CLIENT: PRIMATEXCO INDONESIA at Sambon-Batang （Pekalongan）
Hereafter: PRIMA Project 1 & PRIMA Project 2

 Title: Energy Saving for Textile Factory Facility Cooling byHigh-efficiency Centrifugal Chiller
CLIENT: NIKAWA TEXTILE INDUSTRY at Mitra Karawang Jaya
Hereafter: NIKAWA Project

Both Companies shall be operating their chillers and collecting
the Electricity consumption data for MRV.
PT. Ebara Indonesia(PTEI) shall maintain the chillers for keeping
good condition.

Three Project’s Location
PT NIKAWA TEXTILEINDUSTRYPT PRIMATEXICOINDONESIA
Apply 2 Projects

COMPARISON Between
Reference & Project Chiller
Both Projects Chiller’s Capacity: 1758kW (≒ 500USRt)
Item
Chilled Water
Leaving Temp.
Cooling Water
Leaving Temp.
Actual COP
Adjusted COP

Unit

Reference
Chiller

PRIMAProject 1
Project 2℃

7141411℃

3736.9

36.9

36.9

5.33
5.33

7.66
6.01

7.814
6.13

7.097
6.22

PRIMA

NIKAWA
Project

Project 1

Project 2

NIKAWA
ProjectRegisteration No.

ID001

ID005

ID004

Estimated Emission
Reduction

117 tCO2/Y

152 tCO2/Y

205 tCO2/Y

Methdology (ID-AM002)

17-Sep-2014

Registeration

31-Oct-2014

8-Sep-2016

8-Sep-2016

Item

Ebara Refrigeration Equipment & Systems Co., Ltd. & PT. Ebara Indonesia

FEATURE of EBARA CHILLERS
 PT. Ebara Indonesia has a service center inIndonesia for client and his satisfaction.
 We have communicated to the chillers
through Internet for continuous monitoring(24 hrs).
 Even if something wrong, our monitoring
center will advise to our local engineers tosolve the issue.

 Using high efficiency chillers, End user savethe electricity cost 10% or more comparedPrima Project-1 chiller
with conventional chillers.
Operating from Feb.
2014

Ebara Refrigeration Equipment & Systems Co., Ltd. & PT. Ebara Indonesia

JCM Registered Project at 2013
in Indonesia

PRIMATEXCO INDONESIA

2013 ProjectOperation
Training

OFFICE AREA

Project-2 Chiller This chiller isoperating from April 2015 .

PT PRIMATEXCO INDONESIA
Amount of GHG Reduction (Project-1 & 2)YearProject 1

OperatingMonth

ConsumedkW

ReducedtCO2/P

Emission
Factors

Start Feb. 2014 & Operating up to now

2013

1.5 Months

173,472

100.8142014

12 Months

1,436,311

880.8142015

12 Months

1,350,301

830.8142016

9 Months

1,151,033

730.84

Project 2

Start Apr. 2015 & Operating up to now

2015

12 Months

1,325,3901040.814

2016

9 Months

1,233,671

100

0.84

Ebara Refrigeration Equipment & Systems Co., Ltd. & PT. Ebara Indonesia

JCM Registered Project at 2014
in Indonesia

Nikawa Textile Industry

2014 Project Tag

Chiller in the Factory
Operating From Dec. 2014

TrainingNIKAWA TEXTILE INDUSTRY
GHG Reduction (NIKAWA Project )

2014
2015

Operating ConsumedHrs
kW
4 Months
549,945
12 Months 1,787,695

2016

9 Months

Year

1,310,737

ReducedEmission
tCO2/P
Factors
530.8141720.814
1300.84

Chiller is operating from Dec. 2014.

Site Visit by Indonesian JCM Committee Members

Amount of GEG Reduction inIndonesia by Centrifugal Chillers
 We have reduced GHG emission inIndonesia as follows; PRIMATEXCO (1st Project): 254 tCO2 +（417 tCO2)
 PRIMATEXCO (2nd Project): 204 tCO2 +（537 tCO2)
 NIKAWA TEXTILE:
355 tCO2 +（678 tCO2)
 Total
813 tCO2 +（1632 tCO2)
Note:

813 tCO2 was reduced from end of 2013 to end of 2016
and 1632 tCO2 or more will be expected to reduce from 2017
to 2020.
Ebara Refrigeration Equipment & Systems Co., Ltd. & PT. Ebara Indonesia

Technical Transfer
 We have invited few engineers from Indonesia andtrain the chiller technology in Japan for Technicaltransfer.
 Also we have arranged training for both companies
local engineers in Indonesia.

Training In Japan

CONCLUSION
 High Efficiency chiller is expensive. But energy saving model canexpect to save GHG emission.
 In Indonesia, air Conditioning system is one of the biggest marketfor chillers. Too many old chillers are operating.
 Also Textile Industry is one of the biggest export business inIndonesia. Factories are using many old chillers now.
 In Indonesia, Initial cost is one of the most important point for
selecting the chiller. Save energy & stable operation is also
important issue for long time operation. Therefore we would like topromote High efficiency & stable operating chiller for Indonesianenergy situation. Fortunately, we could supply additional chiller toM/S NIKAWA TEXTILE INDUSTRY without any JCM Subsidy program.
 As our conclusion, we would like to try continuously to promotereplacing high efficiency models for GHG emission reduction.
Thank you for your kind attention !!