Ordering information

Single phase input type (1-Stage filter)

NAC/NAM/NAH/NAP series(4-30A) NAC -10 -472 -O
12341 Series Name
2 Rated Current
3 Line to ground capacitor code: Refer to table 1.1.

R

NAP
NAH
NAM
NAC

table1.1 Line to ground capacitor code
Line to ground
Leakage Current
capacitor(Input 125/250V 60Hz) (nominal value)A / 10 A max Not Provided000● ● ● 	  5A / 25 A max
100pF
101
● ● ● 12.5
A / 50 A max
221220pF● ● ● 25
A / 75 A max
331
330pF
● ● ● 37.5
A / 100 A max
471470pF● ● ● 50
A / 150 A max
681 ●
680pF
● ● 75.5
102 ●● ● 	  0.13 mA / 0.25mA max 1,000pF
222 ●● ● 	  0.25 mA / 0.5 mA max 2,200pF
332 ●● ● 	  0.38 mA / 0.75mA max 3,300pF
472 ●● ● 	  0.5 mA / 1.0 mA max 4,700pF

Code*When the line to ground capacitor code isdifferent, the attenuation characteristic isdifferent.

4 Option
D :DIN rail installation type
The terminal cover is retracted inside the unit

DIN rail installation type is option* The dimensions change when the option is set.
Refer to External view.

Features of NAC/NAM/NAH/NAP series-Single Phase 250VAC (1-Stage filter)
Quick and easy push-down terminal-Just connect the wires, push-down and tighten the screws with a screwdriver

NAC : High-attenuation type from 150kHz to 1MHz
NAH : Ultra high-attenuation type from 9kHz to 1MHz

NAM : Low leakage current type
NAP : Outside impulse high-attenuation typeSpecifications
No.

Items

1234567891011121314

Rated Voltage[V]Rated Current[A]Test Voltage (Terminal-Mounting Plate)
Isolation Resistance (Terminal-Mounting Plate)
Leakage current
Voltage drop
Safety agency approval temperatures
Operating temperature
Operating humidity
Storage temperature/humidity
Vibration
ImpactSafety agency approvals
Case size (without projection) /Weight

NAC-04-472
NAC-06-472
NAC-10-472
NAC-16-472
NAC-20-472
NAC-30-472
NAM-04-000
NAM-06-000
NAM-10-000
NAM-16-000
NAM-20-000
NAM-30-000
NAH-06-472
NAH-10-472
NAH-16-472
NAH-20-472
NAH-30-472
NAP-04-472
NAP-06-472
NAP-10-472
NAP-16-472
NAP-20-472
NAP-30-472
AC 1f 250 / DC250
4610162030
2,500 VAC (Cutoff Current = 20mA), 1minute at room temperature and humidity
500 VDC 100MW min at room temperature and humidity
Refer to table 1.1
1.0V max-25 to +85C (Refer to Derating Curve)-40 to +85C (Refer to Derating Curve)
20 to 95%RH (Non condensing)-40 to +85C/20 to 95%RH (Non condensing)
10 to 55Hz, 19.6m/s2 (2G), 3min. Period, 1hour each X, Y and Z axis
196.1m/s2 (20G), 11ms Once each X, Y and Z axis
UL1283, CSA C22.2 No.8 (C-UL), DIN EN60939 VDE0565 Teil3-1, ENEC (At only AC input)
53X41X92 mm [2.09X1.61X3.62 inches] (WXHXD) /300g max (Option : -D refer to external view)

Circuit Diagram

Derating Curve

Case

1CY

LINECY

23LOAD
4Load Factor [%]

10080
60
40
200-40CY : Line to ground capacitor

NA-1-30-204050 55 60

Ambient Temperature [C]: Mounting Plate

September 16, 2021

708090NAC/NAM/NAH/NAP series(4-30A)
External view
This product is shipped in the following condition, because it is equipped with push-down terminals.
1The terminal cover is retracted inside the unit.
2The screws for connecting the terminals are held in the up right position.

Standard Type92

[3.62](2.5)

82 ±0.5[3.23]

2-f4.877[0.19]

Mounting Hole27

[1.06][0.1]

2-Protection Earth8[0.31][3.03]

45 ±0.5

OutputTerminal[0.47]

1253[2.09][1.77]

OutputTerminal

Name Plate[0.59]

15

Input
Terminal

Input
Terminal
6-M4

Mounting Plate(2)¶ Closed the terminal cover[0.08]

Terminal cover

Terminal cover¶ Tolerance : ±1 [±0.04]¶ Weight : 300g max
41[1.61]¶ Mounting Plate : Iron (surface finishing:nickel plating) t=1.0 [0.04]¶ Case : PBT¶ Dimensions in mm, []=inches¶ Terminal block screw tighting torque M4:1.6N-m (16.9kgf-cm) max

DIN rail installation Type92(11)[3.62][0.43]

77[3.03](2.5)
2-Protection Earth

27

[0.1]

[1.06]

8[0.31][0.47]

53[2.09]

OutputTerminal

Name Plate[0.59]

12

OutputTerminal

Input
Terminal
6-M4
Terminal cover

Mounting Plate(2)

Terminal cover¶ Closed the terminal cover[0.08]

15Input
Terminal

41[1.61]¶ Tolerance : ±1 [±0.04]¶ Weight : 300g max¶ Mounting Plate : Iron (surface finishing:nickel plating) t=1.0 [0.04]¶ Dimensions in mm, [[0.35]]=inches¶ Terminal block screw tighting torque M4:1.6N-m (16.9kgf-cm) max
7

DIN rail[0.28](9)¶ Case : PBT¡Note when installing the EMI/EMC
Filter on a DIN rail.
When the EMI/EMC Filter is grounded throughthe DIN rail, the proper noise attenuation may not
be achieved.
Be sure to connect the protection earth (PE) of
the EMI/EMC Filter body to the earth.
At least one PE connection is required.

DIN railName Plate

September 16, 2021

NA-2