DATA SHEETType 8653

AirLINE Field – the valve island – optimised for process
automation• Fieldbus interface CANopen, IO-Link or büS (Bürkert System Bus)
• Easy diagnostics via LC display• Process reliability through pneumatic functions• Optimised for installation in the field (IP65/67)

Product variants described in the data sheet may differ from the product presentation and description.

Can be combined withType description

Type 8652

AirLINE - the valve island
optimised for process
automation
Type ME43
Fieldbus gatewayType 2012
Pneumatically operated
2/2-way globe valveCLASSIC

The valve island Type 8653 AirLINE Field has been especially developed for applications in process automation. New diagnostic functions can be visualised at theLC display, both in clear text and as symbols. This facilitates assignment of thedisplayed messages and helps to save time during start-up and maintenance.
Furthermore the diagnostic message is also available in the controller. This therefore enables a fast overview of the plant status. The hardware design has been
optimised for installation close to the actuator. Thus, an intelligent installation
system allows the valve island to be installed in a wide variety of positions. Needless to say, straightforward installation on the DIN rail is also possible. Moreover,key pneumatic functions ensure increased process reliability. For instance, thenon-return valves in the exhaust air ducts make sure there is no unplanned actuation due to pressure peaks.

Type 2100

Pneumatically operated
2/2-way angle seatvalve ELEMENT for
decentralized automation
Type 8920

Bürkert CommunicatorType 8697
Pneumatic control fordecentralised automationof ELEMENT processvalves

Standard | EU | en | 2023 - 10 - 02 | 04
© Christian Bürkert GmbH & Co. KG, Subject to alteration

Visit product website

Type 8653

Table of contents
1.

General technical data

3

2.

Circuit functions

4

3.

Approvals and conformities

5

3.1..
General notes....................................................................................................................................................................................5
3.2..Conformity........................................................................................................................................................................................5
3.3..Standards..........................................................................................................................................................................................5
3.4..
North America (USA/Canada)...........................................................................................................................................................54.

Materials
4.1..

5

Bürkert resistApp..............................................................................................................................................................................55.

Dimensions

6

6.

Device/Process connections

7

6.1..

7.

Product design and assembly
7.1..

8.

9.4..

8

Bürkert Communicator Software......................................................................................................................................................8

Ordering information
9.1..
9.2..
9.3..

7

Example configuration......................................................................................................................................................................7

Product accessories8.1..

9.

Assignment of circular plug M12, 5-pin............................................................................................................................................7büS/CANopen version......................................................................................................................................................................7IO-Link version..................................................................................................................................................................................7

9Bürkert eShop...................................................................................................................................................................................9Bürkert product filter.........................................................................................................................................................................9
Ordering chart...................................................................................................................................................................................9
Ordering chart Type 8653 büS version.............................................................................................................................................9
Ordering chart Type 8653 CANopen version..................................................................................................................................11
Ordering chart IO-Link version........................................................................................................................................................12
Ordering chart accessories.............................................................................................................................................................14
Fieldbus gateway Type ME43.........................................................................................................................................................14
Accessory for Software Bürkert Communicator.............................................................................................................................14

Visit product website

2 | 14

Type 8653

1.

General technical data

Product properties
Dimensions

Further information can be found in chapter “5. Dimensions” on page 6.

Material
Body
SealMaximum installation width of a valve
islandWidth per station
Manual override
Number of valve positions
Maximum number of valve functions
Switching function/Operating principle
Pneumatic intermediate supply
Performance data
Pressure data
Pressure range
External supply air (auxiliary pilot air)Flow rate QNn value air
Flow rate QNn value air with integrated
P shut-off
Nominal operating mode
Switching time
Electrical data
Operating voltage
Voltage tolerance
Residual ripple (at DC)
Nominal power of each valve
Nominal current of each valve
Position feedback
Protection classPPA
NBR and PUR
48.6 mm. Further information can be found in chapter “5. Dimensions” on page 6.
11 mm
Latching, spring return (optional: lockable)
Max. 4Max. 8Further information can be found in chapter “2. Circuit functions” on page 4.
N/A
Overpressure to atmospheric pressure
Vac.…8 bar
3…8 bar
310 l/min 1.) measured at + 20 °C, 6 bar pressure at valve inlet and 1 bar differential pressure
N/A
Continuous operation (100 % duty cycle)
Measured according to ISO 12238
24 V DC± 10 %1 Vss
0.7 W (0.1 W after power reduction)
29 mA (10 mA after power reduction)
Possible via 8-DI module Type ME44 or 16-DI module Type ME6
III according to DIN EN 61140, VDE 0140

Total current
With fieldbus connection
Current consumption < 400 mA
Medium data
Operating medium
Oil-free or lubricated compressed dry air, neutral gases (5 μm filter recommended)
Compressed air quality
ISO 8573 - 1:2010, Class 7.4.4
Approvals and conformities
Degree of protection
IP65, IP67
North America (USA/Canada)
Further information can be found in chapter “3.4. North America (USA/Canada)” on page 5.
Process/Port connection & communication
Working port
D 6, D ¼
Air supply connection
D 8, D 5/16
Communication module
ME43 or ME63 (Gateway)
Communication interface
PROFIBUS DP
Industrial Ethernet (PROFINET IO, EtherNet/IP, Modbus TCP, EtherCAT,
CC-Link IE Field Basic)
CANopenbüS (for networking with Bürkert devices)
Environment and installation
Installation position
AnyStorage temperature- 10…+ 60 °C
Ambient temperature- 10…+ 55 °C
Accessories
Software Bürkert Communicator
Bürkert Software 2.)
Further information can be found in chapter “8.1. Bürkert Communicator Software” on page8.
1.) The maximum flow rate depends on the valve function.
2.) For commissioning, the Bürkert Communicator software Type 8920  as well as the associated USB büS interface set 1 with Article no. 772426  are required.

Visit product website

3 | 14

Type 8653

2.

Circuit functions

Symbol42141213154214121342141125 1 34214125 134214125 134214125 134214125 1 3Visit product website

5Description
Circuit function C (CF C)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally closed
Circuit function D (CF D)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally open
Circuit function H (CF H)
5/2-way solenoid valve
Servo-controlled, with manual override
Pressure applied via port (1), therefore one of the two ports (2) or (4) is under pressure.
Circuit function L (CF L)
5/3-way solenoid valve
With manual override
In middle position all ports locked
Circuit function M (CF M)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 ventilated
Circuit function N (CF N)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 exhausted
Circuit function Z (CF Z)
5/2-way solenoid valve
Impulse version with 2 coils and manual override
Pressure applied via port (1), therefore one of the two ports (2) or (4) is under pressure.

4 | 14

Type 8653

3.

Approvals and conformities

3.1. General notes• The approvals and conformities listed below must be stated when making enquiries. This is the only way to ensure that the pro­duct
complies with all required specifications.
• Not all available versions can be supplied with the below mentioned approvals or conformities.

3.2. Conformity
In accordance with the Declaration of conformity, the product is compliant with the EU Directives.

3.3. Standards
The applied standards which are used to demonstrate compliance with the EU Directives are listed in the EU-Type Examination Certificate
and/or the EU Declaration of Conformity.

3.4. North America (USA/Canada)
Approval

Description
Optional: UL Listed for the USA and Canada
The products are UL Listed for the USA and Canada according to:• UL 61010‑1 (ELECTRICAL EQUIPMENT FOR MEASUREMENT, CONTROL, AND LABORATORY USE – Part 1:General Requirements)• CAN/CSA-C22.2 No. 61010‑1

4.

Materials

4.1. Bürkert resistApp
Bürkert resistApp – Chemical resistance chart
You want to ensure the reliability and durability of the materials in your individual a­ pplication
case? Verify your combination of media and materials on our website or in our resistApp.
Start chemical resistance check

Visit product website

5 | 14

Type 8653

5.

Dimensions

Note:
Dimensions in mm, unless otherwise stated
Hose connection
ø8 mm

Hose connection
ø8 mm

25108.9
4.3
70

35.5

5461

Hose connection
ø6 mm (alternative 1 of 2)

11.04

6.35

29.25

4.3
25

8.8

48.6

6.5

4.1

11.04

6.35

14

23

4.3

82.2

126.4

103.55138.5

2.5

Hose connection
ø1/4" (alternative 2 of 2)

Visit product website

6 | 14

Type 8653

6.

Device/Process connections

6.1. Assignment of circular plug M12, 5-pin
büS/CANopen version
Assignment of circular plug M12, 5-pin, A-coded, büS/CANopen variant
View of pins
45132Pin
123
45Assignment
SHIELDING
Supply voltage 24 VGND
CAN_H (büS connection)
CAN_L (büS connection)

IO-Link version
Assignment of circular plug M12, 5-pin, A-coded, IO-Link variant, Port Class B
View of pins
45132

7.

Pin12345Assignment
L+ (24 V processor)
P24 (24 V valve unit)
L- (0 V GND processor)
C/Q (IO-Link)
N24 (0 V GND valve unit)

Product design and assembly

7.1. Example configuration
The following graphic shows a network with the example of Fieldbus Gateway Type ME43 and AirLINE Field Type 8653 (büS version).
Industrial Ethernet

24 V DC, GND, CAN_L, CAN_H

Visit product website7 | 14

Type 8653

8.

Product accessories

8.1. Bürkert Communicator Software
Note:
The corresponding communication software can be downloaded from the website Type 8920 .
The Bürkert Communicator is the most important software component of the EDIP (Efficient Device Integration Platform). Various features ofthis universal tool simplify the configuration and parametrisation of devices equipped with a digital CANopen-based interface. With this tool
the user has a complete overview of cyclic process values as well as acyclic diagnostic data. The integrated graphical programming
environment enables the creation of decentralised sub-system control functions. The connection to the PC is established with a USB-CAN
adapter. The adapter is available as an accessory (see “9.4. Ordering chart accessories” on page 14 ).
The Bürkert Communicator enables:• Configuration, parametrization and diagnosis of EDIP devices / networks• Easy and comfortable mapping of cyclic values• Graphical display of process values• Firmware update for the connected EDIP devices• Backup and restoring of device configurations

Visit product website



8 | 14

Type 8653

9.

Ordering information

9.1. Bürkert eShop
Bürkert eShop – Easy ordering and quick delivery
You want to find your desired Bürkert product or spare part quickly and order d­ irectly? Ouronline shop is available for you 24/7. Sign up and enjoy all the benefits.
Order online now

9.2. Bürkert product filter
Bürkert product filter – Get quickly to the right productYou want to select products comfortably based on your technical requirements?
Use the Bürkert product filter and find suitable articles for your application quickly and easily.
Try out our product filter

9.3. Ordering chart
Ordering chart Type 8653 büS version
The following ordering chart lists the part numbers for Type 8653, subdivided according to connection type and circuit function. All valve
positions are equipped with the same operating principle.
Note:
All articles in the following table are equipped with integrated check valves.
SymbolQNn value air

C (CF C)2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally closed

Article no.
D6/D8

Article no.
D¼"/ 5/16"[l/min]270

Switching times
OpeningClosing
[ms]
[ms]
1515309522 309537 

310

15377659 o. r.

4

21412
1

3

1

5D (CF D)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally open

15

4214

12
1

3

Visit product website1

59 | 14

Type 8653

SymbolQNn value air

H (CF H)
5/2-way solenoid valve
Servo-controlled, with manual override
Pressure applied via port (1), therefore one of the twoports (2) or (4) is under pressure.
4

Article no.
D6/D8

Article no.
D¼"/ 5/16"[l/min]270

Switching times
Opening
Closing[ms][ms]2025309529 338890 

290

2025

20030510 o. r.

2902025o. r.

o. r.

290

2025o. r.

o. r.

290

2025

20058986 o. r.

214125 1 3L (CF L)
5/3-way solenoid valve
With manual override
In middle position all ports locked
4214125 13

M (CF M)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 ventilated
4214

125 13N (CF N)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 exhausted
4214125 13

Z (CF Z)
5/2-way solenoid valve
Impulse version with 2 coils and manual override
Pressure applied via port (1), therefore one of the twoports (2) or (4) is under pressure.
4214

125 1 3o. r. = on request

Visit product website

10 | 14

Type 8653

Ordering chart Type 8653 CANopen version
The following ordering chart lists the part numbers for Type 8653, subdivided according to connection type and circuit function. All valve
positions are equipped with the same operating principle.
Note:
All articles in the following table are equipped with integrated check valves.
SymbolQNn value air[l/min]270

Switching times
Opening
Closing
[ms]
[ms]
15
15

310

15

15o. r.

o. r.

270
H (CF H)
5/2-way solenoid valve
Servo-controlled, with manual override
Pressure applied via port (1), therefore one of the two ports(2) or (4) is under pressure.

2025309532 338917 290

20

25o. r.

o. r.

290

2025

o. r.

o. r.

290

2025

o. r.

o. r.

C (CF C)2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally closed

Article no.
D6/D8Article no.
D¼"/ 5/16"

309527 338914 421412
1315D (CF D)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally open
42141214

315214125 1 3L (CF L)
5/3-way solenoid valve
With manual override
In middle position all ports locked
4214125 13

M (CF M)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 ventilated
4214125 13N (CF N)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 exhausted
4214125 13

Visit product website

11 | 14

Type 8653

SymbolQNn value air[l/min]290
Z (CF Z)
5/2-way solenoid valve
Impulse version with 2 coils and manual override
Pressure applied via port (1), therefore one of the two ports(2) or (4) is under pressure.
4

Switching times
Opening
Closing
[ms]
[ms]
2025

Article no.
D6/D8

Article no.
D¼"/ 5/16"

o. r.

o. r.

214125 1 3o. r. = on request
Ordering chart IO-Link version
The following ordering chart lists the part numbers for Type 8653, subdivided according to connection type and circuit function. All valve
positions are equipped with the same operating principle.
Note:All articles in the following table are equipped with integrated check valves.
SymbolQNn value air

Article no.
D6/D8Article no.
D¼"/ 5/16"[l/min]270

Switching times
Opening
Closing[ms][ms]
1515357762 373702 

310

151520002355 o. r.

H (CF H)270
5/2-way solenoid valve
Servo-controlled, with manual override
Pressure applied via port (1), therefore one of the two ports(2) or (4) is under pressure.

2025370110 373703 

2025382177 o. r.

C (CF C)2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally closed
42
1412
1

3

15D (CF D)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally open
4214

12
1

4

3

15

214

12
5 1 3

L (CF L)
5/3-way solenoid valve
With manual override
In middle position all ports locked
4290

214125 13

Visit product website

12 | 14Type 8653

SymbolQNn value air[l/min]290

Switching times
Opening
Closing
[ms]
[ms]
2025

290

2025o. r.

o. r.

290
Z (CF Z)
5/2-way solenoid valve
Impulse version with 2 coils and manual override
Pressure applied via port (1), therefore one of the two ports(2) or (4) is under pressure.

2025371372 o. r.

M (CF M)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 ventilated
4

Article no.
D6/D8

Article no.
D¼"/ 5/16"

o. r.

o. r.

214

125 13N (CF N)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 exhausted
4214125 134214125 1 3o. r. = on request

Visit product website

13 | 14

Type 8653

9.4. Ordering chart accessories
Fieldbus gateway Type ME43Note:• Please note that the ME43 gateway modules are not configured ex works. However, these absolutely must be configured in order to beused in a system. The device description files must be generated with the Bürkert Communicator software before the start-up of asystem.
• Further information can be found in the operating instructions Type ME43 .
Description
Industrial Ethernet gateway (PROFINET IO, EtherNet/IP, Modbus TCP, EtherCAT®)

Article no.

PROFIBUS gateway (PROFIBUS DPV1)

307393 

Gateway büS/CANopen

307391 

Gateway CC Link

307394 307390 Accessory for Software Bürkert Communicator
Description
büS cable extension, M12, cable length: 0.1 m

Article no.

büS cable extension, M12, cable length: 0.2 m772402 büS cable extension, M12, cable length: 0.5 m772403 büS cable extension, M12, cable length: 1 m772404 büS cable extension, M12, cable length: 3 m

772405 büS socket, M12, straight, A-coded

772416 büS plug, M12, straight, A-coded

772417 büS socket, M12, angled, A-coded

772418 

büS plug, M12, angled, A-coded

772419 büS Y plug

772420 büS Y plugfor linking 2 separately supplied segments of a büS network

772421 772492 Termination resistor (directly pluggable)

303833 büS plug, M12, terminating resistor 120 Ω772424 büS socket, M12, terminating resistor 120 Ω

772425 Power supply unit Phoenix Class2 (Type 1573), 85…240 V AC/24 V DC, 1.25 A, NEC Class 2 (UL 1310)

772438 Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 1 A, NEC Class 2 (UL 1310)

772361 Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 2 A, NEC Class 2 (UL 1310)

772362 Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 3.8 A, NEC Class 2 (UL60950 - 1)

772898 Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 10 A

772698 microSD card

774087 USB büS interface set 1 (Type 8923) for connection to the Bürkert Communicator software: includes connection cable(M12 and micro USB), stick with integrated terminating resistor, power supply and software
USB büS interface set 2 (Type 8923) for connection to the Bürkert Communicator software: including büS stick,connection cable to M12 plug, M12 connection cable on micro USB for the büS service interface and Y distributor, cable
length: 0.7 m
License for graphical programming (only required for a running time > 60 minutes)

772426 

Software Bürkert CommunicatorType 8920 772551 567713 1.) Due to lack of space, the M12 single connectors may not be suitable for their simultaneous use on the same side of the Y connector. Please use the available ready-made assembled cable in this case.

Visit product website

14 | 14