Ordering information

Small, Single phase input type: Screwless terminal (1-Stage filter)

ESC/ESM/ESP series

ESC -10 -472
123-O
41 Series Name
2 Rated Current
3 Line to ground capacitor code:Refer to table 1.1.

RCodeES P
ES M
ES C

table1.1 Line to ground capacitor code
Line to ground
Leakage Current
capacitor(Input 125/250V 60Hz) (nominal value)000
A / 10 A max Not Provided● ● 	  5101A / 25 A max
100pF● ● 12.5
A / 50 A max
220pF
221
● ● 25A / 75 A max
330pF
331
● ● 37.5
A / 100 A max
470pF
471
● ● 50A / 150 A max
680pF
681 ●
● 75.51,000pF
102 ●● 	  0.13 mA / 0.25mA max
2,200pF
222 ●● 	  0.25 mA / 0.5 mA max
3,300pF
332 ●● 	  0.38 mA / 0.75mA max
4,700pF
472 ●● 	  0.5 mA / 1.0 mA max*When the line to ground capacitor code isdifferent, the attenuation characteristic isdifferent.

4 Option
D :DIN rail installation type
DIN rail installation type is option* The dimensions change when the option is set.
Refer to External view.

Electric cable is not appended.

Features of ESC/ESM/ESP series-Single Phase 250VAC (1-Stage filter)
Small EMI/EMC Filters that change input-output terminal and protection earth terminal of EA series into-
screwless terminal type
-Torque management is unnecessary with screwless

ESC : Attenuation type from 150kHz to 1MHz
ESP : Outside impulse attenuation type

ESM : Low leakage current typeSpecifications
No.

Items

12345678910
11121314

Rated Voltage[V]Rated Current[A]Test Voltage (Terminal-Mounting Plate)
Isolation Resistance (Terminal-Mounting Plate)
Leakage current
DC resistance
Safety agency approval temperatures
Operating temperature
Operating humidity
Storage temperature/humidity
Vibration
ImpactSafety agency approvals
Case size (without projection) /Weight

ESC-03-472
ESC-06-472
ESC-10-472
ESC-16-472
ESM-03-000
ESM-06-000
ESM-10-000
ESM-16-000
ESP-03-472
ESP-06-472
ESP-10-472
ESP-16-472
AC 1f 250 / DC250
3610162,500 VAC (Cutoff Current = 20mA), 1minute at room temperature and humidity
500 VDC 500MW min at room temperature and humidity
Refer to table 1.1180mW max110mW max
40mW max
20mW max-25 to +85C (Refer to Derating Curve)-40 to +85C (Refer to Derating Curve)
20 to 95%RH (Non condensing)-40 to +85C/20 to 95%RH (Non condensing)
10 to 55Hz, 19.6m/s2 (2G), 3min. Period, 1hour each X, Y and Z axis
196.1m/s2 (20G), 11ms Once each X, Y and Z axis
UL1283, CSA C22.2 No.8 (C-UL), DIN EN60939 VDE0565 Teil3-1, ENEC (At only AC input)
39X30X85 mm [1.54X1.18X3.35 inches] (WXHXD) /170g max (Option : -D refer to external view)

Circuit Diagram

Derating Curve

Case

1LINECY

32CY4LOAD

Load Factor [%]

100
80
60
40200-40
CY : Line to ground capacitor

EA/ES-3-30-204050 55 60

Ambient Temperature [C]: Mounting Plate

October 06, 2021

70

8090

ESC/ESM/ESP series
External view
Standard Type85

[3.35]

78[3.07]

76.2[2.95]

ScrewlessTerminal
OutputTerminal[1.24]

26.5[1.04]

24[0.94]

39[1.54][0.31]

7.75[0.17]

ScrewlessTerminal
Input
Terminal
2-f4.8[0.19] Mounting Hole

31.5 ±0.5Name Plate[0.55]

7Mounting Plate

6-Check hole f2.1
[0.08]
Protection Earth1477[3]75 ±0.5[0.28] [0.28] [0.28]

4.25

ScrewlessTerminal
Input
Terminal

ScrewlessTerminal
OutputTerminal
Strip Gauge

Protection Earth
6-Connection/release button¶ Weight : 170g max[1.18]¶ Mounting Plate : Iron (surface finishing:nickel plating) t=1.0 [0.04]

30

1012MAX MIN

Strip¶ Tolerance : ±1 [±0.04]¶ Case : PBT¶ Dimensions in mm, []=inches¶ Refer to instruction manual for details.

DIN rail installation Type
8.5 +2-185[3.35]

7876.2[0.08]

Protection Earth

ScrewlessTerminal
Input
Terminal

26.5[1.04]

24[0.94]Name Plate[0.55][0.31]

7.75[0.17][1.54]

397

ScrewlessTerminal
OutputTerminal[3]

6-Check hole f2.1

14

77

Mounting Plate[3.07][0.28] [0.28] [0.28]

4.25

ScrewlessTerminal
Input
Terminal[0.33]

ScrewlessTerminal
OutputTerminal

Protection Earth
6-Connection/release button

Strip Gauge¶ Weight : 170g max
30[1.18]

1012
MAX MIN Strip¶ Tolerance : ±1 [±0.04]¶ Mounting Plate : Iron(surface finishing:nickel plating) t=1.0 [0.04]¶ Case : PBT[0.28]

7[0.35](9)¶ Dimensions in mm, [DIN rail]=inches¶ Refer to instruction manual for details.

(4.2)[0.17]¡Note when installing the EMI/EMC
Filter on a DIN rail.
When the EMI/EMC Filter is grounded throughthe DIN rail, the proper noise attenuation may not
be achieved.
Be sure to connect the protection earth (PE) ofthe EMI/EMC Filter body to the earth.
At least one PE connection is required.

DIN railName PlateOctober 06, 2021

EA/ES-4