WARNING:
IF THE INFORMATION IN THESE INSTRUCTIONSARE NOT FOLLOWED EXACTLY, A FIRE OR
EXPLOSION MAY RESULT CAUSING PROPERTYDAMAGE, PERSONAL INJURY OR LOSS OF LIFE.
FOR YOUR SAFETY:
DO NOT STORE OR USE GASOLINE OR OTHER
FLAMMABLE VAPORS AND LIQUIDS IN THE
VICINITY OF THIS OR ANY OTHER APPLIANCE.

GF 3 BVALLAGASH
B-Vent Gas Heater

INSTALLATION:
INSTALLATION AND SERVICE MUST BE
PERFORMED BY A QUALIFIED INSTALLER,SERVICE AGENCY OR LICENSED GAS SUPPLIER.
WHAT TO DO IF YOU SMELL GAS: DO NOT TRY TO LIGHT ANY APPLIANCE.
 DO NOT TOUCH ANY ELECTRICALSWITCHES.
 DO NOT USE THE PHONE IN YOURBUILDING. IMMEDIATELY CALL YOUR GAS
SUPPLIER FROM A NEIGHBORS PHONE.
 FOLLOW YOUR GAS SUPPLIERS
INSTRUCTIONS.
 IF YOU CANNOT REACH YOUR GAS
SUPPLIER, CALL THE FIRE DEPARTMENT.
AVERTISSEMENT:ASSUREZ-VOUS DE BIEN SUIVRE LESINSTRUCTIONS DANS CETTE NOTICE POURREDUIRE AU MINIMUM LE RISQUE DINCENDIEOU POUR EVITER TOUT DOMMAGE MATERIEL,TOUTE BLESSURE OU MORTALITE.
NE PAS ENTREPOSER NI UTILISER DESSENCENI OU LIQUIDES INFLAMMABLES DANS LEVOISINAGE DE CET APPAREIL OU DE TOUTAUTRE APPAREIL.

Installation
and Operation
Instructions
Warnock Hersey

C

US

LINSTALLATION LE SERVICE DOIVENT ETREEXECUTES PAR UN INSTALLATEURQUALIFIE, AGENCE DE SERVICE OU LE
FOURNISSEUR DE GAZ.
QUE FAIRE SI VOUS SENTEZ UNE ODEUR DE GAZ.
 NE PAS TENTER DALLUMER LAPPAREIL
 NE TOUCHEZ A AUCUM NTERRUPTEUR.
 NE PAS VOUS SERVIR DES TELEPHONES SETROUVANT DANS LE BATIMENT OU VOUS
VOUS TROUVEZ.
 APPELEZ IMMEDIATEMENT VOTRE
FOURNISSEUR DE GAZ CHEZ UN VOISIN. SUIVEZLES INSTRUCTIONS DU FOURNISSEUR.
 SI VOUS NE POUVEZ REJOINDRE LE
FOURNISSEUR DE GAZ, APPELEZ LE SERVICEDES INCENDIES.

Model: Allagash B-Vent
Gas Stove

TABLE OF CONTENTS:
WELCOME TO JØTUL
.. ....................3
STANDARDS......................................................4
GENERAL INFORMATION .................. .......4
LOCATION........
............. 5
FLOOR PROTECTION..................
......
6
STOVE CLEARANCES ................
....
6
ALCOVE................................................6
PARALLEL INSTALLATION..................6
CORNER INSTALLATION......................6
MANTEL, CEILING AND TRIM.............6
VENTING REQUIREMENTS................. 7
HEARTHMOUNT...................................8
VENTING GRAPH.................................9GAS CONVERSION......................
....10GAS CONNECTION ..
....................... 12
GAS PRESSURE ..
.......................
12
HIGH ALTITUDE INSTALLATIONS ..............13
AIR SHUTTER ADJUSTMENTS... ............... 14
INSTALLING THE LOG SET........... . 15
INSTALLING DECORATIVE PIPE BRACKETS....15
INSTALLING THE BLOWER..............................16
REMOTE/THERMOSTAT.................................17
SPILL SWITCH OPERATION.............................17
CHECKING THE SYSTEM...................18
OPERATION OF APPLIANCE...........................19
MAINTENANCE..............................................19
REPLACEMENT PARTS....................................21
ILLUSTRATED PARTS .
......................22
LIGHTING INSTRUCTIONS ........Inside Back Cover

Manufactured andDistributed by:

Jøtul A.S.A.
Fredrikstad, Norway
Jøtul North America
Portland, Maine
THIS STOVE IS SHIPPED AS A
NATURAL GAS STOVE ONLY.
IF USE WITH PROPANE IS
DESIRED, THE STOVE MUST BE
CONVERTED TO USE WITH
PROPANE. FOR YOURCONVENIENCE THE STOVE ISSHIPPED WITH A PROPANE
CONVERSION KIT.
SUGGESTED TOOL LIST FOR
INSTALLLATION AND SERVICE:*External regulator (for LPG only)*Piping which complies with local code
*Manual shutoff valve*Sediment trap
*Tee joint*Pipe wrench*Pipe sealant*10mm open end wrench*1/2, 7/16 open end wrench*Phillips head screwdriver*Flat head screwdriver*1/4 nut driver*Gloves*Safety glasses*Torx T20 screwdriver*Leak test solution

THIS OWNERS OPERATING AND INSTRUCTIONS MANUAL IS DESIGNED TO
GIVE YOU A SAFE, EFFICIENT, DEPENDABLE INSTALLATION OF YOUR
ALLAGASH B-VENT GAS STOVE.
PLEASE READ THESE INSTRUCTIONS IN THEIR ENTIRETY AND MAKE THEMAVAILABLE TO ANYONE USING OR SERVICING THE GAS STOVE.

2

WELCOME TO JØTUL:Congratulations on the purchase of your new
Jøtul gas stove.
We at Jøtul are very happy you have made thedecision to warm your hearth with a Jøtul product.
Your new Jøtul Allagash has inherited the benefits
learned from more than 140 years of producing
stoves. Jøtul is the worlds largest manufacturerof solid fuel burning appliances and has been
making cast iron wood and coal stoves since 1853.

28

The Allagash incorporates the most advanced gas
technology with the warm traditional style of castiron. With proper care and operation, your new
Jøtul will last many, many years.

22 3/4The Jøtul Allagash gas stove is a gravity vented
gas fireplace heater. The Allagash B-Vent gas
stove can only be vented vertically directly tothe outside, using type B-vent pipe.

HEIGHT
OF TOPCENTEROF REAR

EXIT IS

27 1/2The Jøtul Allagash gas stove is designed to operateon NATURAL GAS or PROPANE only. For
safe and efficient operation the stove is equippedwith a millivolt gas control valve with a piezo
ignitor. Electrical power is only required when
operating the OPTIONAL forced air blower, if
installed on the stove (part # 129161).

EXIT IS23

13 1/4

Input Rates
The input rate on the Allagash gas stove is 24,000
BTU/hr maximum input on the high setting forboth natural gas and propane, adjusted down to
19,000 BTU/hr minimum on the low setting, forboth natural gas and propane.

4

18 1/2

22 3/4

3

Natural gas

24,000 BTU/hr. maximum input
19,000 BTU/hr. minimum input

Propane24,000 BTU/hr. maximum input
19,000 BTU/hr. minimum input

STANDARDS:

The installation must conform to local codes. Your
local Jøtul dealer can assist you in determining
what is required in your area for a safe and legal
installation. Some areas require a permit to installa gas burning appliance. Always consult your local
building inspector or authority having jurisdiction
to determine what regulations apply in your area.

This appliance complies with National Safety
standards and is tested and listed by ITS,Intertek Testing Services
Middleton, WI
In addition, the Allagash gas stove complies withand has been tested and listed as a gravity vented
gas fieplace heater and listed to:

REMEMBER Your local officials have final
authority in determining if a proposed installationis acceptable. Any requirement that is requestedby the local authority having jurisdiction, that is
not specifically addressed in THIS manual,defaults to local code. In the absence of local
codes, the installation requirements must comply
with the current National codes. In the U.S. theserequirements are established in the National FuelCode, ANSI Z223.1.(NFPA 54). In Canada, thecodes have been established in CAN/CGA B149
Fuel Installation Code.

ANSI Z21.88-1998(NFPA 54)
CSA 2.33-M98 for Canada.
DO NOT ATTEMPT TO ALTER OR
MODIFY THE CONSTRUCTION OF THE
APPLIANCE OR ITS COMPONENTS. ANY
MODIFICATION OR ALTERATION WILL
VOID THE WARRANTY, CERTIFICATION
AND LISTING OF THIS APPLIANCE.

Installer lappareil selon les codes ou reglements
locaux, ou, en labsence de tels reglements, selon
les Codes dinstallation CAN/CGA-B149.

GENERAL INFORMATION:
THIS HEATER MUST BE INSTALLEDAND MAINTAINED BY A QUALIFIEDSERVICE AGENCY.

DO NOT OPERATE THIS STOVE IF ANYPART HAS BEEN UNDER WATER.
Immediately call a qualified service technician
to inspect the heater and to replace any part ofthe control system and any gas control which has
been under water.

The installation and repair of this appliance must
be done by a qualified service person. Failure
to properly install and maintain this heater could
result in an unsafe or hazardous installation,
which may result in a fire, explosion, property
damage, personal injury or loss of life.

Ne pas se servir de cet appareil sil a ete plonge
dans leau, completement ou en partie. Appeler
un technicien qualifie pour inspecter lappareil etremplacer toute partie du systeme de controle ettoute commande qui ont ete plonges dans leau.

This appliance should be inspected before use
and at least annually. More frequent cleaning
may be required due to excessive lint fromcarpeting, bedding material, etc. It is imperativethat control compartments, burners andcirculating air passageways of the appliance be
kept clean.

Do not operate the Allagash gas stove with theglass front removed, cracked or broken.
Replacement of the glass should be done by alicensed or qualified service person. Only remove
glass for routine service. Always handle glass
carefully.

Sassurer que le bruleur et le compartiment descommandes sont propres. Voir les instructions
dinstallation et dutilisation qui accompagnentlappareil.

Pour utilisation avec les portes en verre cerifiers
aved lappareil seulemend ou Ne pas utiliser avec
des portes on verre.

4Hot Surfaces
The Allagash gas stove will, during normal
operation, reach high surface temperatures
therefore:

THIS APPLIANCE MUST NOT BECONNECTED TO A CHIMNEY OR FLUESERVING ANY OTHER APPLIANCE OF
ANY KIND.

·

LOCATION:

·

·
·
·
·
·
·

Due to the high operating temperatures thisappliance should be located out of traffic
and away from furniture and draperies.
Children and adults should be alerted to thehazards of high surface temperatures andshould stay away to avoid burns or clothingignition.
Young children should be supervised while
they are in the same room as the Allagash
gas stove.
Clothing or other flammable materials
should not be placed ON or NEAR the
Allagash gas stove.
Surveiller les enfants. Garder les vetements,
les meubles, lessence ou autres liquides avapeur inflammables loin de lappareil.
NEVER store or use gasoline or any otherflammable vapors or liquids in the vicinityof the Allagash gas stove.
Never burn any other materials in yourAllagash gas stove, it is strictly designed foruse with natural gas or propane fuel ONLY.
Any safety screen, glass or guard removed
for servicing the appliance must be replaced
prior to operating the appliance.

In selecting the location, the aesthetic andfunctional use of the appliance are primaryconcerns; However, proper venting systems andaccess to the fuel supply are also important issues.
Due to the high surface temperatures of the
Allagash, always consider the proximity of traffic
ways, furniture, draperies, etc.
This appliance may be located on or nearconventional construction materials. HOWEVER,
always maintain the proper clearances tocombustibles, as this provides adequate
ventilation air around the appliance.
The following clearances and hearth requirements
are the minimum requirements when installing
the Allagash gas stove near or on combustible
surfaces. Always provide adequate access aroundthe appliance for servicing and proper operation.
A combustible surface is anything that can burn(i.e. sheet rock, wall paper, wood, fabrics etc.).
These surfaces are not limited to those that are
visible and also include materials that are behind
non-combustibles.

Blower/Electrical Hazard
When the Allagash gas stove is installed with theoptional forced air Blower Kit (part #129161) thestove must be electrically grounded in accordancewith local codes or, in the absence of local codes,
with the current NFPA 70- National Electrical
Code or CSA C22.1-Canadian Code.

If you are not sure of the combustible nature ofa material, consult your local fire officials.
Remember, Fire Resistant materials are
considered combustible: they are difficult toignite, but will burn. Also, fire-rated sheet rockis considered combustible.

The Allagash Blower Kit is already supplied witha three-prong (grounding) plug for protection
against shock hazard and should be plugged
directly into a properly grounded three-prong
receptacle.

The Allagsh B-Vent gas stove is not to beconnected or installed using any warm air ductsystem.
Always maintain the proper clearances to theappliance for the proper flow of combustion andventilation air to the stove.

DO NOT CUT OR REMOVE THE
GROUNDING PRONG FROM THE PLUG.
Always unplug the Blower when performing
routine service to the Allagash gas stove.

5

FLOOR PROTECTION:PARALLEL INSTALLATIONThe Allagash gas stove CANNOT be installed
directly on carpeting, vinyl flooring, linoleum or
Pergoã.

2 (50mm) fromdraft hood

If it is desired to install this appliance on any
combustible material OTHER THAN WOOD,
a floor pad must be installed that is either metal,
wood or a listed hearth pad. This floor protection
must extend the full width and depth of theappliance. It is not necessary to remove thecarpeting, vinyl or linoleum from underneath thefloor protection.
Minimum hearth protection
under the Allagash B-Vent gas
stove:
22 3/4 wide X 18 3/4 deep10
(255mm)4
(102 mm)

left sidewall

right sidewall

CORNER INSTALLATION
3
76mm

Note: the hearth requirements are the same whenusing the optional short leg package.
STOVE CLEARANCES:

3
76mm

Minimum clearances for the Allagash B-Vent
gas stove are as follows:
Rear clearance =2(50mm)(measured from draft hood)

Ceiling =18(460mm)(measured from top of stove)
Corner clearance =3(76mm)(measured from rear corners)

MANTEL, CEILING AND TRIM

Right side clearance = 4(102mm)
Left side clearance = 10 (255mm)

MANTEL OR(for access to the lighting instructions)

TRIM DEPTH

19or greater in depth

All venting components must be installed inaccordance with the terms of their listing andmanufacturers instructions. Refer to the pipe
manufacturers instructions for proper pipe
clearances. Any horizontal venting requires a2 (50mm) top clearance off top of pipe.

A

ALCOVE6- 18 in depthB2- 5 in depthC1 trim only

MINIMUM
CLEARANCES TO TOP

Minimum Alcove Width = 41(1042mm)

PLATE OF STOVE(minimum side clearance in an alcove becomes 8
on right side of stove and 10 on left side of stove).
Maximum Alcove Depth = 24(610mm)
Minimum Alcove Height (off stove)= 18(460mm)(minimum height off top casting of stove).

A = 18
(460mm)
B = 12
(305mm)C = 5
(127mm)1 trim = 1 (25mm)

Pipe clearances =see manufacturers listing.

6

VENTING REQUIREMENTS:

 Any UNUSED flue or masonry enclosure can beused as a passage way for venting the Allagash:
PROVIDED the flue is relined using Type B
4 vent or Listed Flexible Gas Liner.

The Allagash is specifically designed to operateusing 4 Type B vent pipe components or a Listed
Flexible gas liner.

 The remaining space around the liner in amasonry or zero-clearance flue CANNOT be
used to vent any other appliance.

FOLLOW THE GUIDELINES LISTEDBELOW FOR THE PROPER VENTING OF
THE ALLAGASH B-VENT STOVE!

 When terminating through the roof refer to theGas Vent Rule for proper vent termination
height. See Figure 1.

 All venting components must be installed inaccordance with the terms of their listing andmanufacturers instructions.
 The minimum height of a vertically terminatedsystem shall be no less than 7', and the
maximum height shall be no more than 35'.
See diagrams page 9.
 With steep roofs, nearby trees, and in
predominant windy conditions, poor draft or
down draft conditions can occur. In these cases,
increasing the height of the vent or high windtermination caps may improve the situation.
 ELBOWS: If an offset or elbow is necessary
in the vertical rise, it is important to support
the vent pipe every three feet, to avoid excessive
stress on the offsets.

Figure 1

 Whenever possible use 45° elbows opposed to
90° elbows. This offers less restrictions for theflow of flue gases.
Maximum number of 90° elbows = three
Maximum number of 45° elbows = four NO venting can terminate horizontally or
below roof eaves.

 Passage through combustibles (walls, ceilings)

must be with Type B venting and must
maintain listed clearances.

 TOTAL MAXIMUM HORIZONTALRUN ANYWHERE IN THE VENTINGCONFIGURATION IS 4 FEET. The distance
between any 45° elbows is considered ahorizontal run. See diagrams page 9.

 It is recommended that any horizontal runs
have an upward slope of 1/4 per foot toward
the termination cap.

 Any Type B vent passing through a roof must  When venting through a thimble into ahave a flashing, storm collar, thimble and aType B cap is required. See diagrams page 9.

masonry flue any venting exposed in the roommust be Type B venting.

 Venting on the Allagash CANNOT be less than  Listed Flexible Gas Liners may not be exposed4 in diameter or greater than 4 in diameter.

in any living space.

7 When decorative 6 pipe is installed to cover
the venting any Listed Flexible Gas liner must
be connected directly to the stoves draft hood.

Allagash B-Vent gas stove vented into amasonry or prefabricated fireplace.
Listed termination
cap required Use of single wall connector pipe as a vent isprohibited for use with the Allagash B-Vent stove.

Storm collar
required A firestop is required at every floor.

Top sealing
achor plate Any venting that is exposed above the firstfloor, regardless of attic space or living space,must be enclosed. Always maintain therequired clearance from all sides of the verticalvent system according to manufacture.

Type B vent or
Listed Flexible
Gas Liner. On
outside chimneys
Jøtul recommends
the use of Type B
vent to help keep
the gases warm andrising.
max. height 35
min. height 7 Installation of any components not
manufactured or approved by Jøtul or failure
to meet all clearance requirements will void
all warranties and could result in property
damage, bodily injury, or serious fire.
 Never modify any venting component, or use
any damaged venting product.
 THE GAS APPLIANCE AND VENTSYSTEM MUST BE VENTED DIRECTLY
TO THE OUTSIDE OF THE BUILDING,
AND NEVER ATTACHED TO A
CHIMNEY SERVING A SOLID FUEL ORGAS BURNING APPLIANCES.

Always maintainthe proper
clearance to mantel
and trim
Maximum
offset is 4 BE SURE TO MAINTAIN THE PROPER
CLEARANCES TO COMBUSTIBLES AS
DEFINED IN THIS MANUAL AND IN
THE INSTRUCTIONS PROVIDED WITH
EACH VENTING COMPONENT.

Recommended
damper sealing plate
to seal flue chamber
to prevent heat loss

 When installing at an altitude above 2000 theminimum vertical rise becomes 12 from thedraft hood.

Allagash B-Vent gas
stove If more than two feet of venting is exposed tothe outside, the entire exterior vent system
must be enclosed in an insulated chase system.

WARNING : FAILURE TO POSITION THE PARTS IN
ACCORDANCE WITH THIS DIAGRAM OR FAILURE TO USE
ONLY PARTS SPECIFICALLY APPROVED WITH THISAPPLIANCE MAY RESULT IN PROPERTY DAMAGE ORPERSONAL INJURY.

8VENTING CONFIGURATIONS FOR THE
ALLAGASH B-VENT
Listed B-Vent
termination cap
required.

Listed B-Vent
termination cap
required.
Maximum total
horizontal
anywhere inventing
configurationis 4 feet.

Maximum
chimney heightoff draft hood
= 35 feet.
NOTE:
When installingat an altitude
above 2000 theminimum
vertical rise
becomes 12
from the drafthood.

Minimum
chimney heightoff draft hood
= 7 feet.

45° or 90°
elbow

Minimum
chimney heightoff draft hood
= 7 feet.

45° or 90°
elbow

NOTE:
When installingat an altitude
above 2000 theminimum
vertical rise
becomes 12
from the drafthood.

Minimum chimney on the Allagash
B-Vent top vent or rear vent = 7 feet.

Maximum horizontal offset anywhere inventing configuration; rear vent or top ventdirectly on the stove or further up
45° or 90° elbows = 4 feet.

Maximum horizontal offset anywhere inventing configuration; rear vent or top ventdirectly on the stove or further up
45° or 90° elbows = 4 feet.

Maximum # of elbows;
90°= three
45°=four

Listed B-Vent termination cap always required.

Listed B-Vent
termination cap
required.

Minimum
chimney heightoff draft hood
= 7 feet.

Maximum total
horizontal offset
anywhere inventing
configuration is
4 feet.

NOTE:
When installingat an altitude
above 2000 theminimum
vertical rise
becomes 12
from the drafthood.

45° or 90°
elbow

45° or 90°
elbow

Listed B-Vent
termination cap
required.
45° or 90°
elbow

Minimum
chimney heightoff draft hood
= 7 feet.

45° or 90°
elbow

NOTE:
When installingat an altitude
above 2000 theminimum
vertical rise
becomes 12
from the drafthood.

Maximumhorizontal
offsetanywhere inventing
configurationis 4 feet.

9

GAS CONVERSION:The Allagash B-Vent gas stove is shipped fromthe factory equipped as a NATURAL GAS unit;
However, the stove is shipped with the necessary
gas conversion kit to convert the stove to burn
PROPANE GAS. These kits contain all thenecessary components needed to complete thetask and ensure safe operation, including labelingthat must be affixed to the stove.
WARNING:THE CONVERSION KIT IS TO BE INSTALLED BY
AN AUTHORIZED JØTUL SERVICE TECHNICIANINACCORDANCE
WITH
THE
MANUFACTURERS INSTRUCTION AND ALL
CODES AND REQUIREMENTS OF THE
AUTHORITY HAVING JURISDICTION. FAILURE
TO FOLLOW THESE INSTRUCTIONS COULD
RESULT IN SERIOUS INJURY OR PROPERTYDAMAGE.
THE QUALIFIED AGENCYPERFORMING THIS WORK ASSUMESRESPONSIBILTY FOR THIS CONVERSION.
IN CANADA:THE CONVERSION SHALL BE CARRIED OUT INACCORDANCE WITH THE REQUIREMENTS OF
THE PROVINCIAL AUTHORITIES HAVINGJURISDICTION AND IN ACCORDANCE WITH
THE REQUIREMENTS OF THE CAN1-B149.1 AND.2 INSTALLATION CODE.

Cet equipement de conversion sera installe parune agence qualifiee de service conformement aux
instructions du fabricant et toutes exigences etcodes applicables de lautorises avoir lajuridiction. Si linformation dans cette Instructionnest pas suivie exactement, un fey, explosion ou
production de protoxyde de carbone peut resulter
blessure personnelle de vie. Lagence qualifieede service est esponsable de linstallation nest
pas propre et complete jusqua loperation delappareil converti est cheque suivant les criteres
etablis dans les instructions de proprietaire
provisionnees avec lequipement.

Tools required:
1/4 Nut driver, 7/16 and 1/2 open end
wrench or deep well socket, 4mm allen
wrench, Torx t20 or slotted screwdriver.
Included in the conversion kit:
1 regulator tower labeled for propane
3 regulator tower screws
1 burner orifice (#54 LPG)
1 pilot orifice ( #30 for LPG, #51 for NG)
Label A - to be completed and adhered to theback of the stove.
Label B - to adhere to the stoves rating plate.
IMPORTANT:
If the forced air blower kit is installed, be sureto unplug blower before proceeding with thisconversion. Any gas supply must be turned
off and disconnected from the valve.
Conversion instructions are also shipped in thestove with the conversion kit.
Gas Conversion Procedure
1. Turn off gas supply to the stove.
2. Lift off top plate (5).
3. Release the glass clips atop the stove andslowly lift glass panel (10) up and out of track.
4. Remove the log set (12) using care not toscratch or damage logs.
5. Lift out the log support (14). Remove the air
divider (15) by lifting the right side and slowly
rotating forward.
6. Remove burner tube (13): Using a ¼ nut
driver remove the two screws securing theburner tube (13) to the stove bottom. Lift out
the burner tube.
7. Change the main burner orifice. Using a ½open end wrench or deep well socket remove
the burner orifice and replace with theappropriate orifice, supplied in the kit.

10

11. Change the variable regulator on the valve (Hi/Lo knob). Using a Torx t-20 screwdriver, remove
the three specialty screws from the front of thevalve regulator. See Figure 4.
12. Remove the regulator tower and the gasket.
BE SURE TO REMOVE THE BLACK
RUBBER GASKETS FROM THE VALVE!!!
See Figure 4.

8. Adjust the air shutter on the burner tube to allow
for the proper mixing of air and gas. See Figure 2.
The correct settings: natural 1/4 open
propane 1/4 open
Figure 2

AIR SHUTTERBURNER TUBE

13. Install the new variable regulator tower with
the new rubber gasket.
Thoroughly tighten new
regulator to valve body.

ATTENTION: Air shutter should never be
LESS than 1/8 open.

BE SURE TO REMOVE
THE BLACK RUBBERGASKET FROM THE
VALVE!!!

WHEN RE-INSTALLING THE BURNER TUBE BE SURE
THAT THE TUBE IS PULLED FORWARD IN THE
MOUNTING HOLES, SECURE WITH THE TWO 1/4SCREWS.

9. Change the pilot orifice. FROM WITHINTHE FIREBOX, PULL THE PILOTHOOD OFF THE PILOT ASSEMBLY.
Using a 4mm allen wrench thread out the pilot
orifice (counter clockwise). Replace with theappropriate orifice: See Figure 3.
#51or natural gas#30 for propane
Tighten orifice into the base of the pilot
assembly. Be sure the orifice is threaded tightly
and flush with the base.
10. Replace pilot hood onto pilot assembly.

Figure 4.

14. Install the identification labels to the stove sothat they can be seen by any person that may beservicing the stove.
15. Reassemble the stove, apply gas to the systemand check for gas leaks including all stove lines
before and after the valve.
NEVER USE AN OPEN FLAME TOCHECK FOR GAS LEAKS.

PILOT HOOD

ATTENTION!! ATTENTION!!
This is very important
Correct gas pressure is essential for efficient andsafe operation of the Allagash B-Vent gas stove.
It is important that the correct gas pressure be
established at the time of the installation. For
more details, see the Gas Pressure section of thismanual on page 13.

PILOT
ORIFICEPILOT ORIFICESCREWS INTO
BASE

ALWAYS REFER TO THE LIGHTINGINSTRUCTIONS ON PAGE 23 OF THISMANUAL WHEN LIGHTING YOUR
ALLAGASH.

Figure 3.

11

MAKING THE GAS CONNECTION:
NOTE: IF THE OPTIONAL FORCED BLOWER KIT(PART # 129161) IS TO BE INSTALLED ON THE
STOVE AT THE TIME OF THE INSTALLATIONOR IN THE FUTURE, THE GAS SUPPLY LINESHOULD BE INSTALLED AS CLOSE TO THE
FLOOR AS POSSIBLE.
USE OF A 90° ELBOW DIRECTLY OFF THE VALVEWILL ALLOW FOR PROPER CLEARANCE FOR
THE BLOWER.

The gas supply line connection is made to the valve
just inside the left rear leg. The Gas supply line
should be a minimum of 3/8" in diameter, or
the appropriate size to provide sufficient gas
pressure to the valve regardless of the input
setting.
The use of Flexible Gas Appliance Connectors is
acceptable in many areas in the U.S.; However,Canadian methods vary depending on local code.
ALL INSTALLATIONS MUST COMPLYWITH LOCAL CODE OR IN THE ABSENCE
OF LOCAL CODE, MUST COMPLY WITH
THE MOST RECENT EDITION OF THE
NATIONAL FUEL GAS CODE ANSI Z223.1/
NFPA 54 OR CAN-B149.
All codes require: a gas shut-off valve (gas cock)and union, to be installed in the supply line, andin the same room as the appliance. This allows
for the disconnection of the stove for servicing
and maintenance. See Figure 5.

Secure all joints tightly using appropriate tools
and sealing compounds (for propane units, be sure
to use compounds that are propane resistant).
Turn on gas supply and test for gas leaks using asoapy water solution. Never use an open flame
to check for leaks.
Leak test:· Mix a 50-50 solution of water and dish soap.
· Light appliance- see lighting instructions on
page 23 of this manual or on the stoves ratingplate.
· Brush or spray all joints and connections withthe soapy water solution.
· If bubbles appear at any connection or seam
or a gas odor is detected, immediately turngas control knob to the OFF position.
Tighten or reconnect the leaking joint and retest
for any gas leaks.
GAS PRESSURE:
Correct gas pressure is essential for efficient andsafe operation of the Allagash gas stove. It is
important that the correct pressure is establishedat the time of the installation.
Proper gas pressure provides a consistent flow ofgas to the appliance and is instrumental inchecking for gas leaks.The gas control valve on
the stove is equipped with pressure test points
for gauge connections. The gauge connections
are located on the front of the valve under the
On/Off/Pilot- knob. Gauge connections are
identified by:
E for inlet or supply pressure (the amount ofgas coming to the valve.)
A for manifold pressure (the amount of gas thatis coming out of the valve to the burner.)

Figure 5
T-handle gas cocks are required in Massachusettsin compliance with code 248CMR.

12

E A
Pressure test point as located on the front of the valve.

The appliance must be isolated from the gas supply
line by closing its individual manual gas shut-off
valve (gas cock) during any pressure testing of
the gas supply piping system that is equal to or
exceeds pressures of 1/2 psig (3.5kPa).
NECESSARY INLET GAS PRESSURES(inches water column)
MIN
MAX
NATURAL GAS
5.0 WC
7.0 WCPROPANE

11.0 WC

13.5 WC

2.2 WC

3.5 WCPROPANE

6.5 WC

10.0 WC

When installing the Allagash in high altitude(above 2000') situations it becomes necessary tocompensate for the thinner air (less volume of
air per cubic foot). Higher altitudes effect theatmospheric pressure and heat value of gaseous
fuels. The lower oxygen content in the air andthe lower gas viscosity require the use of adifferent orifice to achieve efficient, clean
combustion at the burner tube.
In the U.S.
THE DERATING KIT MUST BE INSTALLED BY
AN AUTHORIZED SERVICE TECHNICIAN IN
ACCORDANCE WITH THE MANUFACTURERSINSTRUCTIONS AND ALL CODES AND
REQUIREMENTS OF THE AUTHORITY HAVINGJURISDICTION. THE INFORMATION STICKER
MUST BE FILLED OUT BY THE INSTALLER AND
ADHERED TO THE APPLIANCE AT THE TIME
OF THE CONVERSION. THE QUALIFIED SERVICEAGENCY PERFORMING THIS WORK ASSUMESRESPONSIBILITY FOR THIS DERATING.

NECESSARY MANIFOLD PRESSURES(inches water column)
MIN
MAX
NATURAL GASHIGH ALTITUDE INSTALLATIONS:ALWAYS TEST PRESSURES WITH VALVECONTROL KNOB SET ON HIGH

Symptons of incorrect gas pressure include:
Insufficient gas pressure: Small pilot flame which can result ininsufficient millivolts.
 Little variation in flame picture between HI
and LO settings.
 Insufficient gas to support more than one
appliance causing nusance outages or gas
surges.
Excessive gas pressure: Permanent damage to valve causing complete
appliance shut down.
 Too large a pilot flame resulting in over heatingof the power generator causing shut down.
 Sooting due to impingement and/or incorrectfuel to air mix.

13

In Canada

THIS UNIT HAS BEEN TESTED FOR
INSTALLATION AT HIGH ALTITUDES IN
ACCORDANCE WITH CANADIAN TESTSTANDARD CAN/CGA-2.17.THE DERATINGSHALL BE CARRIED OUT IN ACCORDANCEWITH THE REQUIREMENTS OF THE
PROVINCIAL
AUTHORITIESHAVINGJURISDICTION AND IN ACCORDANCE WITH
THE REQUIREMENTS OF THE CAN1-B-149.1
AND .2 INSTALLATION CODE.

For installations from 2000ft.(610m) to
4500ft.(1370m) the orifice size for:natural gas is a #42
propane gas is a #55
SEE THE HIGH ALTITUDE ORIFICE CHART

on page 14.

For high altitude installations consult the local
gas distributor or the authority having jurisdiction
for proper rating methods. If the installer must
convert the unit to adjust for varying altitudes,
the information sticker must be filled out by the
installer and adhered to the appliance at the timeof the conversion. See Figure 6.

Derating procedure

1.To derate this unit, install the appropriate orifice per the High Altitude chart.
GAS TYPEORIFICESIZE

ELEVATION

JØTULPART #

NATURALGAS

3/32

0- 2000'(0- 610m)

129114

PRO PANE
GAS#54

0- 2000'(0- 610m)

3096145

NATURAL
GAS#42

2001'- 4500'(611- 1170m)

154376kit

PRO PANE
GAS#55

2001'- 4500'(611- 1170m)

750305P
kit

AIR SHUTTER ADJUSTMENT/FLAME
APPEARANCE:THE ALLAGASH B-VENT GAS STOVE ISSHIPPED FROM THE FACTORY EQUIPPEDAS A NATURAL GAS STOVE; THEREFORE, IT WILL BE NECESSARY WHEN
USING THE STOVEWITH PROPANE GASTO ADJUST THE AIR SHUTTER ON THE
BURNER TUBE TO ACHIEVE THE PROPERGAS TO AIR MIX. See Figure 6.

2.Remove the two ¼ hex head screws that holdthe burner tube/log support to the bottom of
the stove.
3.Remove the burner tube/log support to expose
the main burner orifice.
4.Remove the orifice and replace with theappropriate one from the high altitude kit.
5.Be sure to attach the high altitude conversion
sticker provided with the kit to the rating plateon the appliance.
6. It may be necessary to adjust the air shutter
on the burner tube. See the AIR SHUTTER/FLAME APPEARANCE section of thismanual for more details.
This sticker (shown below) is included in all highaltitude kits and must be adhered to the stove
whenever it is converted for high altitude
installations.

The air shutter adjustment can also help achieve
the desired flame appearance. Generally, flame
appearance is a matter of preference, however
most consumers enjoy the warm yellowish flame.
Closing the air shutter - will generate very longyellow flames resulting in soot. Sooting produces
black deposits on the logs, on the inside walls of
the appliance, and potentially on the exterior
termination cap.
Sooting is caused by incomplete combustion in
the flames and lack of combustion air entering
the air shutter opening.
Opening the air shutter - will generate a flamethat is blue and transparent, or an anemic
flame. This flame is generally more efficient but
not as pretty.
Jøtul recommends the following settings for the
Allagash B-Vent gas stove:for use with propane 1/4 open
for use with natural 1/4 open
Figure 7

AIR SHUTTERBURNER TUBE

ATTENTION: Air shutter should never be
LESS than 1/8 open.

Figure 6

REMEMBER: Run the stove for a minimum of
15 to 20 minutes for an accurate representationof the flame appearance- this should be done
before and between any air shutter adjustment.

14

To adjust the air shutter
1.Remove the burner tube and using a phillips
head screwdriver loosen the screw at the air
shutter and adjust accordingly.
2.Be sure to retighten the screw that holds the
air shutter setting.
3.Reassemble the stove and close the door,
allow stove to burn 30 minutes on the HIGH
setting, observing the flame continuously.
4.If the flame appears weak, slow, or sooty,
repeat the process described above until the
flame is as desired.

Figure 8

WARNING:AIR SHUTTER ADJUSTMENTSSHOULD ONLY BE PERFORMED BY AQUALIFIED PROFESSIONAL SERVICETECHNICIAN.

INSTALLING THE LOG SET:The Allagash is equipped with a one piece log set
and is packaged in bubble wrap inside the firebox.
The log set must be removed from the packaging
and arranged in the unit prior to start up of thegas stove. Do not handle the log set with yourbare hands. Always wear gloves to prevent skinirritation from the ceramic fibers.

INSTALLINGDECORATIVEPIPE
BRACKETS: (The use of decorative pipe is
optional and not included with the Allagash BVent stove.)
To install the decorative pipe brackets on the
Allagash simply remove the four 1/4 hex headscrews holding the 4 flue collar on the stove.
See Figure 9.
It is not neccessary to remove the flue collar.
Place the L shaped decorative pipe brackets
on the flue collar and align the holes on thebrackets, flue collar, and draft hood and secure
all three with the four 1/4 hex head screws.
Black or enamel stove pipe can now rest on thethe draft hood of the appliance while the brackets
center the stove pipe over the draft hood.

To install the log set, remove the packaging andplace the log set inside the firebox, centered from Reminder: single wall stove pipe can never beleft to right and completely against the rear wall used as the vent pipe on the Allagash B-Ventof the stove. See Figure 8.
stove.
Embers: the stove is shipped with a package ofglowing embers. These embers should be pea
size and individually spaced across the burner
tube screen. It is best to equally space theseembers for optimum flame appearance. NOTE:YOU DO NOT HAVE TO USE ALL OF THE
EMBERS.
THE CERAMIC FIBER LOGS ANDGLOWING EMBERS CAN IRRITATE YOUR
SKIN. IF THIS HAPPENS, GENTLY WASH
HANDS WITH WARM SOAPY WATER.

15

Figure 9

INSTALLING THE OPTIONALBLOWER:

Connecting the blower wiring harness:

IMPORTANT: IF THE OPTIONAL FORCED AIR
BLOWER KIT (part # 129161) IS TO BE INSTALLEDON THE STOVE AT THE TIME OF THE
INSTALLATION OR IN THE FUTURE, THE GAS
SUPPLY LINE SHOULD BE INSTALLED AS
CLOSE TO THE FLOOR AS POSSIBLE. USE OF A
90° ELBOW DIRECTLY OFF THE VALVE WILLALLOW FOR PROPER CLEARANCE FOR THE
BLOWER.

Mounting the blower:

1. Locate the reflector sheild (28) on the back of
the stove. Remove the cover plate from thereflector shield to allow the blower bracket toslide under the stove.
2. Locate the two raised bosses on the bottom plate(back) of the stove.
3. The blower is mounted to the stove using these
two threaded holes.
4. With the blower bracket and sensor facing upwardalign the two middle mounting holes on the bracket
with the two threaded holes on the bottom of thestove. See Figure 10.
5. Use the two 6mm bolts to attach the blower tothe stove.
6. Be sure to tighten the bolts so that the blower isdrawn upward and tight against the stove bottom.
7. The heat sensor (thermodisc), that is alreadyattached to the blower bracket, should be inserted
under the stove bottom and make contact withthe firebox! See Figure 10.
Middle mounting holes.
Use these holes to mountblower.

1. Lift off the stove top plate.
2. Loosen (BUT DO NOT REMOVE) the 10mm bolt
holding the switch box to the side of the stove(left rear corner of the stove), and lift out theswitch box.
3. Remove the blank switch from the box.
(Hint: break the retaining tabs holding theswitch in the box.)
4. Insert the new HI/OFF/LO switch into thebox.
5. Connect the insulated wires from the blower
to three leads on the HI/OFF/LO switch.
BLACK wire to the HI position, WHITE
wire to the OFF position, and the RED wire
to the LO position. See Figure 11.
6. Retighten the switch box to the side of thestove. Be sure all wires are unobstructed.
7. Replace top plate.
REMINDER:
The blower will ONLY come on when theswitch is in the Hi or Lo position and ONLY
when the sensor (thermodisc) is heated by thestove.
(Approximately 10 - 20 minutes after the stove
has been running).

Sensor(thermodisc)%/$&.+,

:+,7(2))

5('/ 2:Direction
under thestove.

Figure 11

Figure 10

16

INSTALLING THE OPTIONAL
WALL THERMOSTAT OR REMOTE:SPILL SWITCH:

When installing a wall mounted thermostat to
the Allagash, it must be a 750 millivolt DC twowire circut thermostat. The thermostat shouldbe placed in the same room as the heater, typically5 off the floor. Avoid drafty areas or any areathat may effect the accuracy of the thermostat.
The thermostat should be connected to the
Allagash using a minimum of 16 gauge wire witha maximum length of 35 feet of wire.
Connect the two thermostat wire leads to the twolower terminals on the terminal block locateddirectly above the ignitor button. Do not
overtighten the connections. IT IS NOTNECESSARY TO DISCONNNECT ANYOTHER WIRES. See Figure 12.
For the thermostat to work the On/Off/T-Statswitch on the back of the stove must be in the
T-stat position, and the pilot light must be running,as it is the power source for the thermostat.

The Allagash B-Vent gas stove is equipped with avent SPILL SWITCH. This switch stops gas flow
to the main burner in the event that the applianceis not vented or if the venting is blocked.
The spill switch is an important safety device
located on the draft hood of the appliance and iswired directly to the thermocouple (power source
for the stove). The spill switch is a bimetal
sensor that is heat sensitive. In the event thatthe venting is not carrying the exhaust up andout, the heat from the exhaust will trigger theswitch and stop the electrical current to the valve;
thereby stopping gas flow to the main burner.
Spillage: Condition of flue gases failing to exit
the venting system properly and instead flowing
out of the relief opening of the draft hood andinto the dwelling. Condition calls for
immediate examination of the appliance andventing system and corrective action.
Source: HEARTH- Gas Training Manual

Spillage usually occurs due to incorrct vent size,
or incorrct installation. Be sure to read all of theinstallation requirements addressed in this manual
for the proper and safe installation of yourAllagash B-Vent gas stove.
Unexplained outages can be the result of the spill
switch. If you experience unexplained outages,
contact your local Jøtul dealer for assistance.
ANY SERVICE TO THE SAFETY SPILL SWITCHMUST BE DONE BY A QUALIFIED SERVICEAGENCY.

Figure 12
At the thermostat, the two wires should beconnected to the two connections screws on thethermostat base plate per the manufacturers
instructions.
Remote: When using a remote, the remotereceiver should be wired to the terminal block
the same way the thermostat would be. See theinstructions above.

CAUTION:LABEL ALL WIRES PRIOR TO DISCONNECTION
WHEN SERVICING THE CONTROLS. WIRINGERRORS CAN CAUSE IMPROPER AND
DANGEROUS OPERATION. ALWAYS VERIFYPROPER OPERATION AFTER SERVICING THE
APPLIANCE.
ATTENTION:AU
MOMENT
DE
LENTRETIENDES
COMMANDES, ETIQUETEZ TOUS LES FILS
AVANT LE DEBRANCHEMENT. DES ERREURS
DE CABLAGE PEUVENT ENTRAIUNFONCTIONNEMENTINADEQUATETDAGEREUX.

17

CHECKING THE SYSTEM:
1. PURGING THE GAS LINE: When lighting
the appliance for the first time it will take a few
moments to clear the gas line of air. Once thispurge is complete, the appliance will operate as
described in the lighting instructions located on
the stoves rating plate and the back cover of thismanual. All subsequent lightings of the stove
will not require such purging of the gas line.

NO SMOKE OR SOOT SHOULD BE
PRESENT. CHECK LOG PLACEMENT IFANY SOOT OR SMOKE IS DETECTED. IF
SOOT OR SMOKE PERSIST, THE AIRSHUTTER MAY NEED TO BE ADJUSTED.
See Air Shutter/Flame Appearance section of thismanual for proper air shutter settings andadjustments (page 14). Note: the more offsets
on the vent system, the greater the need for an
air shutter adjustment.

2. PILOT FLAME: The pilot flame should be

CAUTION:
DO NOT ATTEMPT TO ALTER THE
FLAME APPEARANCE BY
POSITIONING THE GAS VALVE IN
ANY OTHER POSITION OTHER
THAN THE FULL ON POSITION.

steady, not lifting or floating. The flame shouldbe blue in color around the pilot hood, with tracesof yellow toward the outer edges.
It is imperative that the pilot flame engulf the
top 3/8 of the thermopile (power generator) andthe top 1/8 of the quick drop out thermocouple.
The pilot flame should project out of the pilot
hood 1 at all three ports. See Figure 13.

1/8
(3mm)
Min.

Thermocouple

Pilot Hood
Ignitor1
(25mm)

3- 4

3/8
(8mm)
Min.

5-6

3- 4

Thermopile

Figure 14
Figure 13.
3. BURNER ADJUSTMENT: The Jøtul
Allagash gas stove is equipped with a variable
gas control valve. This valve provides easy
adjustment of the flame height appearance andheat output. To adjust the flame between the HI
and LO setting, rotate the HI/LO knob, locatedin the center of the valve face. Flame height will
adjust approximately 1.0 to 1.5 between the
HI and LO settings. See Figure 14.

Flame appearance on the high setting after
approximately 15 to 20 minutes burning.
Air Inlet Shutter

Pilot Assembly

Burner TubeWARNING:AIR SHUTTER ADJUSTMENTSSHOULD ONLY BE PERFORMED BY AQUALIFIED PROFESSIONAL SERVICETECHNICIAN.

18

OPERATION OF APPLIANCE:
1.

2.

The Allagash B-Vent gas stove is equippedwith an On/Off/T-stat rocker switch or canbe controlled using an optional wallmounted thermostat. A separate switch isprovided for the optional forced air blowerkit.

7. Clean the glass only when necessary. Wipesurface with a clean, dampened, soft cloth.
Follow with a dry, soft towel as desired.
Take care not to scratch the glass surface.
WARNING:
DO NOT USE ABRASIVE CLEANERS ON THE
GLASS. NEVER CLEAN THE GLASS WHEN IT
IS HOT.

When lit for the first time, the Allagash will
emit an odor for several hours. This odor isthe burn-off by-products of internal paints
and lubricants used in the manufacturing
process.

MAINTENANCE:

3.

Condensation may occur on the glass uponeach lighting of the appliance. This fog
will disappear as the appliance heats up.

4.

Keep the controls and the area under theappliance free of debris, vacuum this area
frequently. Always keep the appliance area
clear and free from combustible materials,
gasoline and other flammable liquids.

IMPORTANT:ALWAYS TURN OFF THE GAS SUPPLY TO THE
STOVE AND UNPLUG THE OPTIONAL FORCED
AIR BLOWER KIT IF INSTALLED, BEFORE ANYSERVICE WORK IS PERFORMED ON THE
STOVE.

If and when a vacuum is used on any service
for the stove, ALWAYS be sure the stove is
cold and there are NO hot embers or sparks.
5.

Remember, this appliance has a continuous
burning pilot flame. Exercise caution whenusing products with combustible vapors.

6.

CAUTION: DO NOT OPERATE THISAPPLIANCE WITH THE GLASSREMOVED CRACKED OR BROKEN.
REPLACEMENT OF THE GLASSSHOULD BE DONE BY A LICENSED ORQUALIFIED SERVICE PERSON. USE
ONLY
REPLACEMENTGLASSPROVIDED BY YOUR AUTHORIZEDJØTUL DEALER. NEVER USE ANY
SUBSTITUTE MATERIALS.

WARNING:OBSERVE CAUTION NEAR THE DOOR. THE
GLASS PANEL MAY SHATTER UNEXPECTEDLYIF STRUCK WITH AN OBJECT. ALWAYSHANDLE THE GLASS PANEL WITH CARE. WHENSERVICING THE STOVE ALWAYS PULL THE
GLASS ASSEMBLY STRAIGHT UP FORREMOVAL.

The Allagash B-Vent gas stove and its venting
system should be inspected before use and at least
annually by a qualified service technician.

General cleaning: The firebox should be
vacuumed out annually to remove any surfacebuild up. Be sure to vacuum or wipe off the pilot
assembly and burner orifice and burner tube. Also,
when vacuuming the log set, be sure to handle it
carefully as it is very fragile.
Gasket inspection: It is important that the glass
gasket be inspected at least annually. Examine
the rope gasket for signs of deterioration and makesure the gasket has a positive seal. This isimportant to prevent combustion gases fromescaping into the room. Replace the gasket if
necessary, refer to the replacement parts list on
page 21.
To remove the glass panel or glass gasket:

1. Lift off the stove top.
2. Release the glass clips atop the firebox.
3. Pull the glass frame assembly straight up and outof the stove.
4. Lay the asssembly on a flat surface and lift themetal tabs that secure the glass panel to the frame.
5. Install the new glass panel and gasket in the glass
frame and secure with metal tabs. Do not overtighten tabs as this could break the glass.
ALWAYS USE JØTUL AUTHORIZED PARTS.
NEVER USE ANY SUBSTITUE PARTS.

19

Always replace any damaged or broken parts on
the Allagash with JØTUL AUTHORIZEDPARTS ONLY. These are available through yourAutorized Jøtul dealer. Never use any substituteparts on your Allagash B-Vent gas stove.

SERVICE LOG:
First Year
Name of Technician__________________The Allagash and its venting system should be
inspected annually or semi-annually by a qualified
service person or agency.

Company Name______________________

With proper care and maintenance, your appliancewill provide you with years of enjoyment. If you
experience any problem or inconsistency withyour Jøtul Allagash B-Vent gas stove, contact yourauthorized Jøtul dealer for assistance.

Work Performed______________________To expedite the proper service for your appliancethe following information will help your dealer
determine what you will need for parts and service.
RETAIN THIS MANUAL FOR REFERENCE
AND MAKE IT AVAILABLE TO ANYONEUSING OR SERVICING THE STOVE.
MODEL NAME:

Allagash B-Vent Stove

Date of service_________________________________________________________SERVICE LOG:
Two Year
Name of Technician__________________
Company Name_____________________
Date of service______________________SERIAL NUMBER:__________________________

Work Performed_____________________DATE OF PURCHASE:___________________________________________________________AUTHORIZED DEALER:_____________________NAME OF INSTALLER:______________________TYPE OF FUEL:_____________________________WAS STOVE CONVERTED?___________________NOTES:SERVICE LOG:
Third Year
Name of Technician___________________
Company Name______________________
Date of service_______________________
Work Performed_________________________________________________________

20

ALLAGASH B-VENT PARTS LIST
Cast Iron Parts / Enamel Colors
1
2
3
4
5
6
7
*
9
10
11
*
*
12
13
*
14
15
16
17
18
*
19
20
21
22
23
24
25
26
*
*
*
*
27

PART
Left Door
Right Door
Front PanelSide PanelTop
Bottom Plate
Legs Single
Short Leg Set
Top Cover

MATTE
10390392
10390492
10390192
10296710390292
10390092
10192592
35007410406592

Door Pins
Glass Clips
Glass Assembly
Glass Panel only
Gasket only (7/16 tadpole)
Log SetBurner Tube
EmbersLog Support
Air Divider
Air Deflector
Exhaust Baffle
Firebox
Latch Keeper
Heat Exchanger Gasket
Heat Exchanger
Draft Hood, Lower
Draft Hood, Upper
Flue Starter Collar
Cover Plate Draft Hood
Rear Shroud
Spill Switch
Wiring Harness -Spill Switch
Spill Switch Wire - 32 in.
Spill Switch Wire - 35 in.
Wire Tie
Box, On/Off/T-stat

BLU/BLK
10390327
10390427
10390127
10203310390227
10390027
10196635007510406527
125960129135154337129113129124 (6ft.)
129122129121129123129132129320129109129310129180129149129313129186129184129185129189129183129179129449154350154389154374129157129148Hardware
Leg Bolts (m6x20)
Washer for Leg Bolts
Bolt- Side Wall to Front (m6x20)
Bolt- Front to Base (m6x20)
Washer- Side to Front
Washer- Firebox to Base
Nut- Firebox to BaseSide Clips Bolts (m6x12)
Door Clip Bolts (m6x12)
Valance Screws (#10x1/2)
Door Washers

IVORY
GREEN
10390329 10390332
10390429 10390432
10390129 10390132
10224610203232
10390229 10390232
10390029 10390032
102251
10192532
35011735007432
10406529 10406532
*
28
29
*
30
*
*
*
*
*
*
*
*
*
*
*
*
*
*
*
*
*
*
*

INDIGO
10390336
10390436
10390136
10312810390236
10390036
10312335007465
10406536

ON/OFFSwitch Only
Reflector Shield
ValanceWiring Harness -On/Off Switch
Spud Plate Assembly
Orifice Holder
Jam Nut for holder
Pilot Assembly NG
Gasket Pilot assembly
Pilot Orifice NG
Pilot Orifice LP
Pilot Line
Thermocouple
Thermopile
Electrode with wire
Burner Orifice- NG 3/32
Burner Orifice- LPG #54
Ignitor Button
Ignitor Bracket
B-Vent Valve NG
B-Vent Valve LP
Brass Elbow
Main Gas Line (complete)Terminal Block

129153129175129106154319154346 NG
1291281291521294711291161294721294731294461294473094527129173129114309614539025733902576154915154916129129154372129154* not illustrated

Accessories
117117120004117117117117120004120004117910117130117130117917117588

Conversion Kit to NG
Conversion Kit to LP
Wall Thermostat
Blower Kit w/Rheostat
RemoteScreenFloor Bracket Kit

154375154348750003129161750002129174750304

Only use replacement parts from an Authorized Jotul Dealer.
For the name of the dealer nearest you, call 207 797-5912
or write to:
Jotul North America
400 Riverside Street
Portland, ME 04104

21

GF3 BV Allagash Illustrated Parts Breakdown
23
22

20

24

21
5

4

19

26

25

18
27

17

4

16
28
15
10

14
6

3

9

13

12

11
30

2
1
29
7

22

LIGHTING INSTRUCTIONSFOR YOUR SAFETY, READ BEFORE LIGHTING.
WARNING:IF YOU DO NOT FOLLOW THESE INSTRUCTIONS EXACTLY, A FIRE OR EXPLOSION MAY
RESULT CAUSING PROPERTY DAMAGE, PERSONAL INJURY, OR LOSS OF LIFE.

A. This appliance has a pilot which must be lit
by hand. When lighting the pilot, follow these
instructions exactly.
B. BEFORE LIGHTING, smell all around theappliance area for gas. Be sure to smell next
to the floor because some gas is heavier than
air and will settle to the floor.
WHAT TO DO IF YOU SMELL GAS: Extinguish any open flame.
 Open windows.
 Do not light any appliance.
 Do not touch any electrical switches.
 Do not use any phone in your building.
 Immediately call your gas supplier from aneighbors phone.

 If your gas supplier cannot be reached, call thefire department.
C. Use only your hand to push in or turn the gas
control knob. Never use tools. If the knob will notpush in or turn by hand, do not try to repair it.
Call a qualified technician. Force or attempted
repair may result in a fire or explosion.
D. Do not use this appliance if any part has been
under water. Immediately call a qualified service
technician to inspect the appliance and to
replace any part of the control system and any
gas control which has been under water.

LIGHTING INSTRUCTIONS
1. STOP! Read the safety information above.
2. Access the lower controls.
3. Turn the stove ON/OFF switch to OFF, or set thethermostat to lowest setting (if used).
4. Confirm that the gas supply line shut-off valve is open.
5. Push in gas control knob slightly and turn clockwise
to OFF.
NOTE: Knob cannot be turned from PILOT to OFF
unless the knob is pushed in slightly. Do not force.
ON

PILOT

Control
Knob

OFF

CONTROL VALVE

6. Wait five (5) minutes to clear out any gas. If you thensmell gas, STOP! Follow B in the safety information
above on this page. If you do not smell gas, go to thenext step.
7. Push in gas control knob slightly and turn counterclockwise
to PILOT.

8. Push in control knob all the way and hold in.
Immediately light the pilot by triggering the spark
ignitor (push the red button repeatedly) until pilot
lights. Continue to hold the control knob in forabout one minute after the pilot lights. Releaseknob and it should spring back. The pilot should
remain lit. If it goes out, repeat Steps 5 through 8.
 If knob does not
return when released,stop and immediately
call your service
technician or gas
supplier.
 If pilot will not stay
lit after several tries,
PILOT ASSEMBLY
turn the control knob
to OFF and call your service technician or gas
supplier.
9. Turn gas control knob counterclockwise
to ON.
10.Turn the stove ON/OFF switch to ON, or set
thermostat (if used) to desired temperature.

TO TURN OFF GAS TO THE APPLIANCE:
1. Turn ON/OFF switch to OFF. The pilot will remain lit fornormal service.
2. For complete shutdown, turn ON/OFF switch to OFF.

3. Access the lower controls.
4. Depress gas control knob slightly and turn clockwise
to OFF. Do not force.

Stoves and fireplaces must be installed to conform to local and national building regulations. Before preparing for the installation of
the appliance, it is important that the instructions issued with the unit are carefully read an strictly adhered to. Jøtul pursues a policyof constant product development. Products supplied may therefore differ in specification, color and type of accessories for those
illustrated and described in the brochure.
Jøtul vise sans cesse a ameliorer ses produits. Cest pourquoi, il se reserve le droit de modifier les specifications, couleurs etequipementsans avis prelable.

Jøtul ASA

P.O. Box 1411
N-1602 Fredrikstad, Norway

Jøtul North America
400 Riverside Street
Portland, ME 04104

December 2000.4

129450