Ordering information

Small, Single phase input type (1-Stage filter)

EAC/EAM/EAP series

EAC -10 -472
123-O
41 Series Name
2 Rated Current
3 Line to ground capacitor code: Refer to table 1.1.

RCode

EA P
EA M
EA C

table1.1 Line to ground capacitor code
Line to ground
Leakage Current
capacitor(Input 125/250V 60Hz) (nominal value)000
A / 10 A max Not Provided● ● 	  5101100pF
● ● 12.5 A / 25 A max
221
A / 50 A max
220pF● ● 25331
330pF● ● 37.5 A / 75 A max
471
A / 100 A max
470pF● ● 50681 ●680pF● 75.5 A / 150 A max
102 ●● 	  0.13 mA / 0.25mA max 1,000pF
222 ●● 	  0.25 mA / 0.5 mA max 2,200pF
332 ●● 	  0.38 mA / 0.75mA max 3,300pF
472 ●● 	  0.5 mA / 1.0 mA max 4,700pF*When the line to ground capacitor code isdifferent, the attenuation characteristic isdifferent.

4 Option
D :DIN rail installation type
The terminal cover is retracted inside the unit

DIN rail installation type is option* The dimensions change when the option is set.
Refer to External view.

Features of EAC/EAM/EAP series-Single Phase 250VAC (1-Stage filter)-Small size
-Quick and easy push-down terminal
Just connect the wires, push-down and tighten the screws with a screwdriver

EAC : Attenuation type from 150kHz to 1MHz
EAP : Outside impulse attenuation type

EAM : Low leakage current typeSpecifications
No.

Items

1234567891011121314

Rated Voltage[V]Rated Current[A]Test Voltage (Terminal-Mounting Plate)
Isolation Resistance (Terminal-Mounting Plate)
Leakage current
DC resistance
Safety agency approval temperatures
Operating temperature
Operating humidity
Storage temperature/humidity
Vibration
ImpactSafety agency approvals
Case size (without projection) /Weight

EAC-03-472
EAC-06-472
EAC-10-472
EAC-16-472
EAC-20-472
EAC-30-472
EAM-03-000
EAM-06-000
EAM-10-000
EAM-16-000
EAM-20-000
EAM-30-000
EAP-03-472
EAP-06-472
EAP-10-472
EAP-16-472
EAP-20-472
EAP-30-472
AC 1f 250 / DC250
3610162030
2,500 VAC (Cutoff Current = 20mA), 1minute at room temperature and humidity
500 VDC 500MW min at room temperature and humidity
Refer to table 1.1
180mW max
110mW max
40mW max
20mW max
10mW max
6mW max-25 to +85C (Refer to Derating Curve)-40 to +85C (Refer to Derating Curve)
20 to 95%RH (Non condensing)-40 to +85C/20 to 95%RH (Non condensing)
10 to 55Hz, 19.6m/s2 (2G), 3min. Period, 1hour each X, Y and Z axis
196.1m/s2 (20G), 11ms Once each X, Y and Z axis
UL1283, CSA C22.2 No.8 (C-UL), DIN EN60939 VDE0565 Teil3-1, ENEC (At only AC input)
39X30X85 mm [1.54X1.18X3.35 inches] (WXHXD) /170g max (Option : -D refer to external view)

Circuit Diagram

Derating Curve

Case

1LINE
2CYCY

3LOAD
4Load Factor [%]

10080
60
40
200-40CY : Line to ground capacitor

EA/ES-1-30-20

4050 55 60

Ambient Temperature [C]: Mounting Plate

October 06, 2021

708090EAC/EAM/EAP series
External view
This product is shipped in the following condition,because it is equipped with push-down terminals.
1The terminal cover is retracted inside the unit.
2The screws for connecting the terminals are held in the up right position.

Standard Type85

[3.35]

75 ±0.5[2.95]

72

2.5

2-f4.8[0.19] Mounting Hole

11.5

[1.54][1.24]

12.7

21[0.83][0.45]

31.5 ±0.5

2-M4
OutputTerminal[0.38]

9.7

Terminal cover

Mounting Plate

Name Plate

Input
Terminal[0.1]

Terminal cover

M4
Protection Earth¶ Tolerance : ±1 [±0.04]¶ Weight : 170g max¶ Mounting Plate : Iron (surface finishing:nickel plating)㹲=1.0 [0.04]¶ Case㸸PBT¶ Dimensions in mm, [ ]=inches¶ Terminal block screw tightening torque M4㸸1.6N࣭m(16.9kgf࣭cm)max

30[1.18]

2¶ Closed the terminal cover[0.08]

2-M4

Protection Earth[0.5]

Terminal coverM439[2.83]

DIN rail installation Type+2

8.5 -185[3.35][0.33]

72[2.83]

11.5

M4[1.54]

12.7

9.7

21

[0.83]

39

2-M4
OutputTerminal

Name Plate

Terminal cover[0.1][0.45][0.38]

2-M4
Input
Terminal

2.5
Mounting Plate[0.5]

Terminal cover

M4

Protection Earth

Terminal coverProtection Earth[0.28]¶ Tolerance : ±1 [±0.04]¶ Weight : 170g max¶ Mounting Plate : Iron (surface finishing:nickel plating)㹲=1.0 [0.04]¶ Case㸸PBT¶ Dimensions in mm, [ ]=inches¶ Terminal block screw tightening torque M4㸸1.6N࣭m(16.9kgf࣭cm)max

7[0.35](9)30[1.18]

2[0.08]¶ Closed the terminal cover

DIN rail(4.2)[0.17]¡Note when installing the EMI/EMC
Filter on a DIN rail.
When the EMI/EMC Filter is grounded throughthe DIN rail, the proper noise attenuation may not
be achieved.
Be sure to connect the protection earth (PE) ofthe EMI/EMC Filter body to the earth.
At least one PE connection is required.

DIN railName Plate

October 06, 2021

EA/ES-2