タイプ ME63
FieldConnect

フィールドバスゲートウェイ

取扱説明書

予告なく技術的変更を行うことがあります。
© Bürkert Werke GmbH & Co. KG, 2020–2021
取扱説明書2110/01_EU-ML_00815318/ドイツ語原本の翻訳版

タイプ ME63

目次
1

取扱説明書...................................................................................................................................................................6
1.1

表記...................................................................................................................................................................6

1.2

用語の定義.......................................................................................................................................................62

使用目的.......................................................................................................................................................................73

基本的な安全注意事項..............................................................................................................................................74

一般注意事項..............................................................................................................................................................8

5

6

7

4.1

連絡先...............................................................................................................................................................8

4.2

保証...................................................................................................................................................................8

4.3

ウェブサイトで閲覧できる情報.......................................................................................................................8

製品説明.......................................................................................................................................................................95.1

一般的な説明...................................................................................................................................................95.2

装置の機能.......................................................................................................................................................9

5.3

システムモニタリング.....................................................................................................................................10テクニカルデータ.......................................................................................................................................................116.1

適合性.............................................................................................................................................................11

6.2

規格.................................................................................................................................................................11

6.3

動作条件.........................................................................................................................................................11

6.4

電気データ......................................................................................................................................................11

6.5

装置ラベリング...............................................................................................................................................11

6.6

産業用イーサネット.......................................................................................................................................12
6.6.1

PROFINET IO................................................................................................................................................126.6.2

EtherNet/IP..................................................................................................................................................12

6.6.3

Modbus TCP................................................................................................................................................12

6.6.4

EtherCAT.......................................................................................................................................................13

6.6.5

CC-Link IE field basic................................................................................................................................13

6.6.6

OPC UA..........................................................................................................................................................13

設置.............................................................................................................................................................................147.1

装置の取付け.................................................................................................................................................14

日本語

3

タイプ ME63﻿

7.2

製品を電気接続します..................................................................................................................................14
7.2.1

7.3

接続の割り当て...........................................................................................................................................15

供給電圧.........................................................................................................................................................16

8

MICROSDカード........................................................................................................................................................179

外部コントローラによるコミッショニング................................................................................................................19

10

9.1

büSネットワークの配線.................................................................................................................................19

9.2

コミッショニングファイルとプロセスデータおよびパラメータの説明.......................................................199.3

高度なゲートウェイ機能................................................................................................................................19BÜRKERTコミュニケーターによるコミッショニング................................................................................................20
10.1 操作インターフェース....................................................................................................................................20
10.2 装置をBürkertコミュニケーターと接続する................................................................................................20
10.3 装置をPLCネットワークに統合するためのプロトコル設定........................................................................21
10.3.1プロトコルの選択......................................................................................................................................21

10.3.2EtherCATアドレス（ステーションエイリアス）を入力します.........................................................21

10.3.3

PROFINET、EtherNet/IP、Modbus TCP、またはCC-Link IE field basicアドレスを入力します........................................................................................................................................................21

10.4 フィールドバスゲートウェイの構成..............................................................................................................2210.4.1

ゲートウェイ構成のダウンロード..........................................................................................................2210.4.2

既存のゲートウェイ構成を編集する....................................................................................................2210.4.3

ゲートウェイ構成を再作成する.............................................................................................................23

10.5 büSネットワーク構成.....................................................................................................................................33
11

WEBサーバーによるコミッショニング......................................................................................................................34
11.1 Webサーバーの機能.....................................................................................................................................34
11.2 Bürkertコミュニケーターを介してWebサーバーを有効化する................................................................34
11.3 ウェブサーバーへの接続を確立する...........................................................................................................34
11.4 Webサーバーでログインする.......................................................................................................................35
11.5 パスワード.......................................................................................................................................................36
11.5.1

パスワードを変更する..............................................................................................................................36

11.5.2

パスワードを工場出荷時設定にリセットする...................................................................................36

11.6 装置構成.........................................................................................................................................................36
4

日本語タイプ ME63
﻿12

OPC UA.......................................................................................................................................................................37
12.1 一般的な説明.................................................................................................................................................37
12.2 OPC UAとの接続の確立...............................................................................................................................37
12.2.1装置の設定...................................................................................................................................................37

12.2.2OPC UAクライアントの設定...................................................................................................................38

12.3 サーバー証明書.............................................................................................................................................38
13

ディスプレイエレメント..............................................................................................................................................40
13.1 バスステータスを表示するためのLED.........................................................................................................40
13.1.1PROFINET IO................................................................................................................................................40

13.1.2EtherNet/IP..................................................................................................................................................41

13.1.3

Modbus TCP................................................................................................................................................42

13.1.4

EtherCAT.......................................................................................................................................................43

13.1.5

CC-Link IE field basic................................................................................................................................44

13.2 装置ステータス表示用LED...........................................................................................................................4514

BÜRKERTコミュニケーターメニュー........................................................................................................................46
14.1 「ウェブサーバー」および「OPC UA」構成範囲...........................................................................................46
14.2 構成範囲「PROFINET」、「EtherNet/IP」、「Modbus TCP」およびCCリンクIEフィールド・ベーシッ
クのメニュー...................................................................................................................................................47
14.3 「EtherCAT」構成範囲のメニュー...............................................................................................................48
14.4 「一般設定」構成範囲のメニュー................................................................................................................49

15

トラブルシューティング.............................................................................................................................................52
15.1 エラーコードの説明.......................................................................................................................................53

16

アクセサリ...................................................................................................................................................................56
16.1 パッシブディストリビューター.......................................................................................................................56
16.1.1

テクニカルデータ.......................................................................................................................................56

16.1.2

電気データ...................................................................................................................................................57

16.1.3

サイドリッドを開閉する...........................................................................................................................57

16.1.4接続の割り当て...........................................................................................................................................57

16.2 büSアクセサリ................................................................................................................................................58
17

保管.............................................................................................................................................................................5918

廃棄処分.....................................................................................................................................................................59

日本語

5

タイプ ME63
取扱説明書

1

取扱説明書

取扱説明書は本製品のライフサイクル全体について説明しています。本説明書は操作場所の手の届く所に保管してください。
安全に関する重要な情報。
▶ 本説明書をよくお読みください。
▶ 安全注意事項、適正使用および使用条件を遵守してください。
▶ 本機を使用する者は本説明書をよく読んで理解する必要があります。

1.1

表記
警告

危険な状況に陥る可能性についての警告。
▶ 遵守しない場合、重傷を負う、または死亡する可能性があります。

注意
潜在的危険性についての警告。
▶ 遵守しない場合、軽症または中程度の傷害を負う可能性があります。

注意
物的損害についての警告。
▶ 遵守しない場合、装置やシステムが損傷する可能性があります。
重要な追加情報、ヒントおよび推薦事項を示します。

本取扱説明書あるいは他の文書の情報の参照指示です。
危険を防ぐための指示のマーキング。
実行する必要のある作業手順をマークします。
結果を示します。
MENU

1.2

ソフトウェアのインターフェーステキスト表示。

用語の定義

用語

説明

装置

フィールドバスゲートウェイ タイプ ME63

büS

ビュルケルトシステムバス ―ビュルケルトが開発したCANopenプロトコルに基づく通信バス

6

日本語

タイプ ME63
使用目的

2

使用目的

フィールドバスゲートウェイタイプ ME63は、büSフィールドバスパティシパントと産業用Ethernet PLCとの間のプロセス値のフィールドバスコンバーターとして使用されます。
タイプME63は、フィールドバスプロトコル
PROFINET、EtherNet/IP、Modbus TCP EtherCAT、CCリンクIEフィールド・ベーシックをサポートしています。
▶ 装置は必ず適切に使用してください。製品を適切に使用しない場合、人、周囲のシステムおよび環境に危険が及ぶ可能性があります。
▶ 製品は、Bürkert が推奨する、
もしくは承認する場合にのみ、他社の製品やコンポーネントと組み合わせて使用
してください。
▶ 製品は、完全な状態でのみ操作してください。
▶ 安全で欠陥のない操作のための前提条件は、適切な輸送、保管、設置、コミッショニング、操作およびメンテナンスです。
▶ ご使用の際には、許容データ、動作条件および使用条件を遵守してください。
この情報は、契約書、取扱説明書
および製品に記載されています。

3

基本的な安全注意事項

この安全注意事項は、取付けや稼働時、メンテナンスに際して発生する偶発事象や事故を考慮していません。事業者は、現地の安全規則をスタッフに関するものも含めて遵守する責任を負います。

一般的な危険状況。
怪我を防ぐために以下の点に留意してください。
▶ 装置は完全な状態で、取扱説明書に従ってのみ使用してください。
▶ 装置を改造したり、機械的なストレスを与えないでください。
▶ 意図しない電源オンから装置やシステムを保護してください。
▶ 訓練済み専門技術者のみが設置及びメンテナンス作業を行うことができます。
▶ 装置は地域の規制に従って設置してください。
▶ 電源が遮断された後はプロセスの再始動が制御されていることを確認してください。
▶ 技術上の一般規則を遵守してください。

注意
UL認証済み製品に関する注意事項:▶ 製品は、SELV/PELV 電圧 (クラスIII) での使用にのみ適しています。
▶ 製品は、屋内 (乾燥した場所) での使用を想定して設計されており、湿気の多い場所には適していません。
▶ 電気設備の構築に関する国内および国際的な規定に従ってください。
▶ 接続済みの外部電気回路を、二重または強化タイプの絶縁 (SELV/PELV) によって主電源から電気的に分離します。
▶ 設置の完了時に過電流保護を用意します。
▶ 製品の過電圧カテゴリはII、汚染度は2となっています。

7

日本語タイプ ME63
使用目的

注意
静電気による危険がある部品およびアセンブリ。
製品には帯電した静電気（ESD）に過敏に反応する電子部品が含まれています。静電気を帯びた人員や物品との接触はこれらの部品の損傷につながります。最悪の場合は、この部品が直ちに破壊されたり、コミッショニング後に故障したりします。
▶ 急激な静電気放電による損傷の可能性を最小限に抑えるか、
または回避するために、EN 61340-5-1 の要件を満たしてください。
▶ 電子部品を電源電圧時に接触させないでください。

4

一般注意事項

4.1

連絡先

日本
Burkert Japan Ltd.
セールスセンター〒 112-0005
東京都文京区水道1-12-15 白鳥橋三笠ビル
電話番号 +81 35804 5020
Fax +81 35804 5021
E-Mail: info.jpn@burkert.com
インターナショナル
連絡先は当社のウェブサイトでご覧になれます：
www.burkert.com

4.2

保証

保証の前提条件は、指定された使用条件に留意のうえでの製品の適正使用です。

4.3

ウェブサイトで閲覧できる情報

Bürkert製品についての取扱説明書とデータシートは以下のインターネットサイトでご覧になれます：
http://country.burkert.com

8

日本語タイプ ME63
製品説明

5

製品説明

5.1

一般的な説明フィールドバスゲートウェイはビュルケルト製品の中央制御ユニットです。FieldConnect タイプME63は、ビュル
ケルトフィールド装置の内部通信を産業用Ethernetやフィールドバスのすべての一般工業規格に送信するフィー
ルドバスゲートウェイで構成されています。

X1

X5

X2

X6

X3

X7

X4

X8
LED装置状態
2個のねじのあるリッド
microSDカードスロット
X01、X02：
Dコードによる接続
X03 (IN)、X04 (OUT):
Lコード接続、24 V DC
アース接続

挿図 1：

タイプME63のビュー

5.2

装置の機能

• büSと産業用イーサネットとの間のフィールドバスコンバーター、• フィールドバス1とフィールドバス2のパティシパント間でプロセス値を交換します。
装置

フィールドバス 1

フィールドバス 2

ME63

büS

PROFINET

ME63

büS

EtherNet/IP

ME63

büS

Modbus TCP

ME63

büS

EtherCAT

ME63

büS

CC-Link IE field basic

ME63

büS

OPC UA

表 1：

フィールドバスゲートウェイアプリケーション
9

日本語

タイプ ME63
製品説明

5.3

システムモニタリング

システムモニタリングは、NAMURステータスに応じて、ゲートウェイに接続されているbüS装置を制御します。
シス
テムモニタリングは、次のようにBürkertコミュニケーターで設定します。
General settings > Parameter > System monitoring
Diagnosticsメニュー項目は、ゲートウェイが全体の状態として受け入れるbüS装置からのメッセージタイプを設定するのに使用します。すべてのタイプを設定すると、ゲートウェイにタイプごとのメッセージが表示されます。
たとえば、接続された装置が「メンテナンス」
ステータスの場合、ゲートウェイに「少なくとも1台のbüS装置がス
テータス：メンテナンス」というメッセージが表示され、NAMURLEDがステータスを引き継ぎます。ただし、優先
度の高いエラーがない場合に限ります。
次の条件が満たされると、機能が保証されます：• ゲートウェイ構成が、6個以上のBürkertコミュニケーターバージョンで作成されている• 構成に、製品カタログが使用されている。各装置に装置IDが割り当てられている• 各büS装置について、NAMURステータスがゲートウェイ構成の循環値として追加されている• 各装置のNAMURステータスが、ゲートウェイに接続されている
PROFINETの特殊機能：
メニュー項目 General settings > System monitoring > Single diagnostics of the system devices で、以下を設定します：接続されたbüS装置でエラーが発生すると、NAMURステータスの対応するスロットにアラームが送信されます（「PROFINETアラームアクティブ」）。

10

日本語

タイプ ME63
テクニカルデータ

6

テクニカルデータ

6.1

適合性

製品は、EU適合宣言書に基づいてEU指令に準拠しています（該当する場合）。

6.2

規格

指令への適合性を証明するために適用される基準は、EU型の検査証明書および/あるいはEU適合宣言書で確認することができます（該当する場合）。

6.3

動作条件

注意
高温と多量の霜による機能障害。
▶ 指定された環境温度の範囲外では装置を使用しないでください。
周囲温度

–20 °
C～+60 °
C

素材

ハウジング：ポリカーボネート
ポッティング：WEVOPUR 552 FL、
ナチュラル

使用高度

海抜 2000 m まで

6.4

電気データ

供給電圧

24 V

消費電力

エレクトロニクス < 2 W
センサ/アクチュエータの電源供給は、1接続部 (X1～X8) あたり4 Aに制限されています。

最大電力

すべての出力で32A//740W

保護等級

IP65/67 (接続に保護キャップ装着されている場合のみ)

UL製品

UL認証過電流保護付きSELV/PELV、UL/IEC 61010-1 表18に準拠した設計

保護クラス

DIN EN 61140 (VDE 0140)準拠の3

6.5

±10%

装置ラベリング
性能データ（周囲温度、IP保護等級電圧、消費電力）

Tamb: -20 °C...+60 °C
IP 67
System Power: 24 V
Output Power: 24 V

2000 mA
2 A per Port PDmax: 16 A

チューブコネクタアイコン

PIN/PORT ME63 Ethernet X01 (IN), X02(OUT) Power X03/X04 CAN Ports X1-X7 CAN+Power X8 (IN)

1
2
3
4
5

TD+
RD+
TDRD-

Us(+24V)
GND_ULGND UsUL(+24V)FE

CAN_GND
24V
GND
CAN_H
CAN_L

CAN_GND
24V
GND
CAN_H
CAN_L

ピン割り当て
挿図 2：

装置のラベリング11

日本語

タイプ ME63
テクニカルデータ

6.6

産業用イーサネット

6.6.1

PROFINET IO

トポロジー検出

LLDP、SNMP V1、MIB2、Physical Device

最小サイクル時間

10 ms

IRT

サポートなし

MRP媒体冗長性

MRPクライアント（サポートあり）

その他のサポートされている機能

DCP、VLANプライオリティタギング、Shared Device

伝送速度

100 MBit/s

データトランスポート層

Ethernet II、IEEE 802.3

PROFINET IO仕様

V2.3

（AR）Application Relations

装置はIO-AR（x 2）、
スーパーバイザーAR（x 1）およびスーパーバ
イザーDA AR（x 1）までを同時に処理できます。

PROFINETインターフェース

2ソケットM12

6.6.2

定義済みの標準オブジェクト

IDオブジェクト (0x01)
メッセージルーターオブジェクト(0x02)
アセンブリオブジェクト(0x04)
接続マネージャー(0x06)
DLRオブジェクト(0x47)
QoSオブジェクト(0x48)
TCP/IPインターフェースオブジェクト(0xF5)
Ethernetリンクオブジェクト(0xF6)

DHCP

サポートあり

BOOTP

サポートあり伝送速度10および100 MBit/s

二重モード

半二重、全二重、
自動ネゴシエーション

MDIモードMDI、MDI-X、Auto-MDIX

データトランスポート層

Ethernet II、IEEE 802.3

Address Conflict Detection（ACD）

サポートありDLR（リングトポロジー）

サポートあり内蔵スイッチ

サポートありCIPリセットサービス

Identity Object Reset Service タイプ0と1

EtherNet/IPインターフェース

2ソケットM12

6.6.3

12

EtherNet/IP

Modbus TCP

Modbusファンクションコード

1、2、3、4、6、15、16、23

モード

メッセージモード：サーバー

伝送速度

10および100 MBit/s

データトランスポート層

Ethernet II、IEEE 802.3

日本語

タイプ ME63
テクニカルデータ

6.6.4

EtherCAT

周期入出力データの最大数

512バイト

周期入力データの最大数

1024バイト

周期出力データの最大数

1024バイト

非周期通信（CoE）

SDO
SDOマスタースレーブ
SDOスレーブスレーブ（マスター容量に応じて）タイプ

複合スレーブ

FMMUs

8

同期マネージャ4

伝送速度

100 MBit/s

データトランスポート層

Ethernet II、IEEE 802.3

6.6.5

CC-Link IE field basic

占有ステーションの数

1～16

非周期通信

SLMPサーバー

データトランスポート層

Ethernet II、IEEE 802.3、100 MBit／s

CC-Linkインターフェース

周期データ61450 (UDP)
ディスカバリーおよびSLMPサーバー 61451 (UDP)
SLMPパラメータ 45237(UDP)
SLMP通信 20000 (UDP)

6.6.6

OPC UA

納品時、OPC UAサーバーは、無効になっています。
OPC UAサーバーは、次のプロトコルでバックグラウンドで実行されます。
• PROFINET IO• EtherNet/IP• Modbus TCP
サーバーOPC UAの機能の有効化と無効化は、Bürkertコミュニケーターで設定します。
OPC UA > Parameter > Enable OPC UA

OPC UA
Parameter

Maintenance

Enabling OPC UA

挿図 3：

Off

OPC UA、有効化

OPC UAの有効化の後、OPC UAサーバーの詳細設定が表示されます（チャプター「12」を参照）。
13

日本語

タイプ ME63
設置

7

設置
警告

不適切な取付けによる怪我の危険。
▶ 設置作業は、必ず、本取扱説明書および製品を理解した技術者が行ってください。
▶ インストール作業は、必ず適切なツールを使用して行ってください。

7.1

装置の取付け装置は、完全に組み立てられた状態で出荷されます。ビュルケルト以外は装置を変更することはできません。

→ 2本のねじ（M4）と2個のワッシャー（DIN125 準拠）を使用して、製品を平面上に取り付けます。締め付けトルク
1 Nmを遵守してください。

これらの装置には、干渉電流の放電とEMCの安定性のためのアース接続があります。

注意
静電気放電による誤動作。
製品の静電気放電は誤動作の原因となります。
► 製品を機能アースに接続します。
電磁場による危険。
機能アース（FE）が接続されていない場合、EMC 法の条件は満たされません。
► 製品を機能アースに接続します。
▶ 取り付け面が接地されていない場合は、接地ストラップまたはFEラインを使用してください。M4ねじを使用して、アースストラップまたはFEラインを設置点に接続します。

7.2

製品を電気接続します
UL認証済み製品に対する要件:▶ 製品は必ず適切な定格値を持つUL認証済み (CYJVまたはPVVA) ケーブルで接続してください。
▶ ケーブルの最高許容温度は105°Cとなります。
▶ 通信に使用されるEthernetケーブルを建物の外に敷設しないでください。
▶ ポートに接続されている外部回路は、主電源から電気的に分離し、通信ネットワークへの絶縁の破壊から保護する必要があります。

注意
製品が正しく機能し、干渉を回避するための前提条件：▶ 必ず編組またはフォイルシールド付きのシールドケーブルを使用してください。
保護等級を確保します。
▶ 使用していない接続部に保護キャップを装着してください。

→ タイプに応じて、ピンを接続します。
14

日本語

タイプ ME63
設置

ポート

機能

ピン1

ピン2

ピン3

ピン4

ピン5

X01 (IN)、X02(OUT)

Ethernet

TD+

RD+

TD-

RD-

–

X03 (IN)、X04 (OUT)： 電源(+24 V)

GND

GND(+24 V)FE

X1–X3、X5–X8 (OUT)

CAN+電源CAN_GND

24 V

GND

CAN_H

CAN_L

X04 (IN)

CAN+電源CAN_GND

24 V

GND

CAN_H

CAN_L

表 2：

接続の割り当て

7.2.1

接続の割り当て

接続X01、X02

3

4

2

1

ピン

割り当て

機能

1

TD+

データ送信+

2

RD+

データ受信+

3

TD-

データ送信-

4

RD-

データ受信-

接続M12、X01、X02 (ソケット)、Dコード

表 3：

接続X03、X04

FE
1

4

2

3
FE

4

1

3

2

ピン

割り当て

機能

1

24 V

電源1

2

GND

電源 2

3

GND

電源1

4

(24 V)

電源 2

5

FE

シールド

M12接続、X03（プラグ）、X04 (ソケット)、Lコード

表 4：

接続 X4、X1-X3、X5-X8

4

ピン

割り当て

機能

1

FE/CAN_GND

シールド

1

2

2

24 V

電源

3

GND

電源

3

4

4

CAN_H

büS通信

5

CAN_L

büS通信

2
表 5：

5

3

5

1
接続M12、X4 (プラグ) およびX1-X3、X5-X8 (ソケット)、Aコード

15

日本語

タイプ ME63
設置

7.3

供給電圧

Aコード接続による供給、最大4 A、自動検出
リバース保護によって、
バックフローが防止されます

24 V/32 Aソース 1

24 V/32 Aソース 2
Lコード接続による供給、最大32 A

挿図 4：

電源オプション

2つの電源（AコードとLコード）が接続されている場合、Aコード電源による逆流が無いようにしてください。
タイプ
ME63の場合、逆流はリバース保護によって防止できます。
モジュールがM12Aコード（X4）経由だけで電源を供給される場合、リバース保護は自動的に切り替わります。

16

日本語

タイプ ME63
microSDカード

8

MICROSDカード

装置固有の値とユーザー設定は、microSDカードに保存して別の装置に転送することができます。
microSDカードはバックアップ用には適していません。装置のmicroSDカードを後で再び挿入すると、最後に保存されたデータは復元されません。microSDカードの機能は、データ交換に限られています。
注意！
装置を工場出荷時設定にリセットすると、SDカードに保存されているデータもリセットされます。
新たに挿入されたmicroSDカードは、装置の再起動時に既存のデータがチェックされます。
これに応じて、データが引き継がれるか、または上書きされます：• microSDカードにはデータは含まれていません。
既存の装置固有の値とユーザー設定は、microSDカードに保存されます。
• microSDカードには、装置と互換性のあるデータが含まれています。
microSDカードのデータは、装置によって引き継がれます。既存の装置固有の値とユーザー設定は上書きされます。
• microSDカードには、装置と互換性のないデータが含まれています。
装置は、独自の装置固有の値とユーザー設定でmicroSDカードのデータを上書きします。

注意
挿入されたmicroSDカードは特別な産業用バージョンで、特に高い耐久性と耐熱性があります。
► 市販のmicroSDカードを使用しないでください。
装置用のmicroSDカードは、Bürkert販売店でのみ入手してください。

Micro SDカードを挿入します
microSDカード

シール
リッド

挿図 5：

Micro SDカードを挿入します注意
電源電圧がかかった状態で取り外すと、データが失われ、SDカードが損傷する可能性があります。
► 電源電圧が印加されている間は、
SDカードを取り外さないでください。

17

日本語

タイプ ME63
microSDカード

電源電圧が印加されている間にSDカードを挿入することは可能です。
SDカードが装置によって認識されるため、再起動が必要です。
microSDカードの取外し：→ ＋ドライバーで2本のねじを緩め、リッドを開きます。
→ ロック解除するには、ロックされたmicroSDカードの端を押します。
→ microSDカードを取り外します。
交換装置へのmicroSDカード挿入：挿入時は挿入方向に注意してください。

→ microSDカードをカードスロットに挿入します。microSDカードが所定の位置にはめ込まれていることを確認してください。

注意
リッドをネジで固定する際、保護等級を確認してください。
► シーリング材が正しく取り付けられているか点検します。
► リッドをネジで締めるする際、最大締め付けトルク0.4 Nmを順守してください。

→ リッドをネジで締めます。

18

日本語

タイプ ME63
外部コントローラによるコミッショニング9

外部コントローラによるコミッショニング

9.1

büSネットワークの配線
büSネットワークの配線の詳細については、次のリンクを参照してください：
büSネットワークの計画に関するガイド

9.2

コミッショニングファイルとプロセスデータおよびパラメータの説明
各プロジェクト計画ソフトウェアに必要なコミッショニングファイルは、構成中に作成されるか、構成者が使用できるようにします。

コミッショニングファイルの設置での注意事項については、使用しているプロジェクト管理ソフトウェアのドキュメ
ントを参照してください。

9.3

高度なゲートウェイ機能
制御モード（通信設定）、制御ワード（循環コマンドの実行）、
オブジェクトルート機能（その他のbüSオブジェ
クトへのアクセス）に関する情報は、http://country.burkert.com → タイプME63 → 取扱説明書「フィールドバスの説明」にあります

19

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

10BÜRKERTコミュニケーターによるコミッショニング
ソフトウェア「Bürkertコミュニケーター」は、Bürkertのホームページから無料でダウンロードできます。
ソフ
トウェアに加え、アクセサリとしてUSB-büSインターフェースセットが必要です。
この章では、Bürkertコミュニケーターの基本的な取り扱いを説明します。Bürkertコミュニケーターソフトウ
ェアの使用に関する詳細情報は、ビュルケルトホームページ(https://country.burkert.com/ →8920 →「取扱説明書」のダウンロード)にあります。

10.1

操作インターフェース
インターフェースの追加（USB-büSインターフェースで接続）

ナビゲーション領域

COMMUNICATOR
File

Device Edit

View

Options

Tools

Help

General settings

Home page
Desktop

Parameter

Graph

büS

1

Diagnostics Maintenance

Alarm limits

büS on COM3

Diagnostics

Gateway ME63

PDO configuration

EtherCAT

Configuration provider

General settings

System monitoring

100%

Zoom

装置の構成範囲（例：プロトコル名
EtherCAT）
装置

メニュー
詳細ビュー P arameters Diagnostics Maintenance

挿図 6：

Bürkertコミュニケーターの用語の説明

10.2

装置をBürkertコミュニケーターと接続する

Bürkertコミュニケーターと装置間の接続は、büsネットワーク経由またはbüSスティックを使用して確立できます。
20

日本語タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング→ BürkertコミュニケーターをPCにインストールします。
→ USB-büSインターフェースセットを使用して、製品とPC間の接続を確立します。
büS ネットワーク内の製品には必要ありません。

→ Bürkertコミュニケーターを起動します。
→ メニューバーのアイコンインターフェースを追加するための Add interface をクリックします。

→ büS Stick または büS via network を選択します。
→ Complete。
 装置はBürkertコミュニケーターに接続されており、ナビゲーション領域に表示されます。

10.3

装置をPLCネットワークに統合するためのプロトコル設定

10.3.1プロトコルの選択(Protocol name) > Parameters > Change protocol > Protocol→ 右側のドロップダウン・メニューでプロトコルを選択します。
10.3.2EtherCATアドレス（ステーションエイリアス）
を入力しますEtherCAtアドレス指定は、デフォルトでEtherCATポートへの物理接続によって実行されます。必要に応じてコント
ローラーに設定すると、ゲートウェイのステーションエイリアスも設定できます。
(Protocol name) > Parameter > EtherCAT settings > Station Alias または Wizard→ アドレスを入力します。有効なアドレス：0～65536。

アドレスが有効範囲外の場合、装置はエラーメッセージを出します。

10.3.3

PROFINET、EtherNet/IP、Modbus TCP、またはCC-Link IE field basicアドレスを入力
します

Modbus TCPでは、Ethernetパラメータの設定が必須です。
(Protocol name) > Parameter > (Protocol name) settings >Start setup wizard→ パラメータを入力します。
Ethernetパラメータ：• IP operation mode は、EtherNet/IP、工場出荷時設定でのみ設定可能です: Fixed IP address• DNS compatible name はPROFINETでのみ設定できます• Fixed IP address 工場出荷時設定：192.168.0.100• Network mask 工場出荷時設定：255.255.255.0• Standard gateway 工場出荷時設定：192.168.0.1

21

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

プロトコル設定、セットアップウィザード

挿図 7：

メニュー項目 IP parameter settings に、IPパラメータの確認という項目が作成されます。

10.4

フィールドバスゲートウェイの構成設定されたプロトコルの名称（プロトコル名）は、Bürkertコミュニケーターの構成範囲に表示されます。
フィールドバスプロ 入力値
トコル

出力値

値の総数

入力バイト

出力バイト

バイトの総数PROFINET

128

128

256

512

512

1024

EtherNet/IP

128

128

256

504

504

1008

Modbus TCP

128

128

256

512

512

2048

EtherCAT

128

128

160

512

512

1024

CC-Link field basic 128

128

256

512

512

2048

表 6：

最大プロセス値

10.4.1

ゲートウェイ構成のダウンロード

以前のプロジェクトの構成ファイルが存在する場合、装置は直接構成することができます。
(Protocol name) > Parameters > Gateway configuration > Download a gateway configuration file

→ Select Load device configuration to device を選択します。

10.4.2

既存のゲートウェイ構成を編集する(Protocol name) > Parameter > Gateway configuration > Creating a gateway configuration→ Edit existing configuration 選択する。
→ 構成を編集する。詳しくは、「10.4.3」章参照してください。

22

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

10.4.3

ゲートウェイ構成を再作成する(Protocol name) > Parameter > Gateway configuration > Creating a gateway configuration→ プロトコルを選択します。
→ Start new configuration 選択します。
 構成ウィザードが開きます。構成アシスタントで、次のように設定します。
一般設定を編集します

10.4.3.1

Create a gateway configuration

General settings
General device settings

Product code

65017

Product family

Gateway

Product name

MEX3

Description

Gateway

入力に関する情報は表6を参照してください：入力フィールドの意味

Default network settings
IP address of the gateway

192.168.0.100

Network mask

255.255.255.0

Standard gateway

192.168.0.1

Advanced

Cancel

挿図 8：Continue

ゲートウェイ構成、一般設定

名称

意味

General settings
Product code

装置の固有番号（商品番号や自分で決めた番号など）。
複数の装置を使用する場合に重要：各装置に固有のコードを割り当てます。

Product family

PLCの中に装置グループを割り当てるのに使用します。

Product name

PLCでの、装置の表示名。

Description

装置の説明

表 7：

入力フィールドの意味→ ターゲットシステム（PLC）の装置記述ファイルの一般設定を調整します（必要な場合）。
→ Continue を選択します。

23

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

10.4.3.2

ゲートウェイ構成の入力と出力の宣言
Create a gateway configuration

Declare inputs and outputs- Products- Electromotive valves
332x E_Process_Valve
336x E_Process_Valve328x Motor Control Valve+ Process and control valves+ Valve islands+ Sensors...

Groups/devices
EVA

0030739000000001
Inputs and outputs% EVA_POS– EVA_SP_IO– EVA_PV_IO- Input values
General number %Binary value
Namur device status
Route
Density...

l/min

EVA_SPdigitalO- Output values
General number %Binary value
Namur device status
Route
Density...

Name

EVA_SPdigital

Value type

Flow rate [l/min]

Data type

Floating point number

Default value

0 l/min

CANopen compatible* Highlighted entries arepresent on the current network
Back

Unit conversion

PLC単位：

Flow:Litres per

CancelContinue

1.製品（）および入力値と出力値の選択
2.入力と出力の宣言
例：宣言用に選択された出力（背景が灰色）選択された入力および出力の概要  
選択した装置/装置グループの表示（削除するにはXをクリック）
挿図 9：

ゲートウェイ構成、入力、出力の宣言

1.入力と出力の選択：
宣言する入力と出力は、製品またはプロセス値を選択することにより決定されます。

→ 製品とプロセス値のリストは+をクリックして開きます。
büSネットワークのプロセス値が強調表示されます。

装置の追加：→ ドラッグ＆ドロップまたはダブルクリックして製品を追加します。
24

ダイアログボックス Add device(s)  では、入力と出力の宣言の値が事前定義されています。

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニング

Add device(s)Settings

Values per device

Device name(prefix for all value names)

EVA

Number1

Maximum possible number of inputs

128

Maximum possible number of outputs

128^

Device configuration
Positioner
Process controller

O

Forecast

CMDdigital

Generated values: 3

EVA_POSEVA_NamurStatus
EVA_CMDdigitalO

i REAL General number %i UINT8 Namur device status
REAL

General number %Cancel

挿図 10：i POS
i CMD
i SP_IO
i PV_IO
i CMD_IO
i XCO_DO1
i XCO_DO2
i DigitalIni CMD_GW
i SP_GWi PCOinactiv_GW
i ExrError_GW
i NamurStatusi PV_UserUnit

OK

ゲートウェイ構成; 製品の追加

ダイアログボックスで次の設定を行います：→ Device name の適用または変更（最大20文字）

この名前は、プロトコル固有のグループ化とネットワーク内のより適切な割り当てに使用されます。

→ 装置の Number を選択します。
→ Device configuration を選択します（選択オプションがある場合）。
→ Values per device を適用または別の値を選択します。
値の名前は上書きによって変更できます。

プロセス値の追加：→ ドラッグ＆ドロップまたはダブルクリックして入力値と出力値を追加します。
同じ単位の複数の値を同時に追加する：→右マウスキーでその単位を、続いて Add multiple ウィンドウをクリックします。

25

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

値のコンテキスト定義
• 入力値
記号： i
入力値はbüSフィールドバスゲートウェイから取得され、PLCによって読み取られる値です（büSフィールドバス
パティシパント → フィールドバスゲートウェイ → PLC）
• 出力値
記号：O
出力値は、PLCによってbüSフィールドバスパティシパント/フィールドバスゲートウェイに書き込まれる値です。

出力値

PLC

出力データのその他のプロセス

入力値

挿図 11：

入力データのその他のプロセス

入力値

büSフィールドバ
スパティシパント
出力値

構成; PLCからbüSフィールドバスパティシパントへのプロセス値の変換タイプ

2.値のプロパティの調整：
値のプロパティの調整は、標準からの逸脱が必要な場合にのみ必要です。

→ 概要で宣言する入力値または出力値をクリックします。
選択した値はグレー表示されます。
宣言のデフォルト値は右下に表示されます。

デフォルト値の意味。
デフォルト値は、装置起動の開始時またはフィールドバスパートナー装置が見つからなかったときに使用します。
宣言には以下を入力または選択します：→ Name を受け入れるか、または調整します。これらの名称は、ターゲットコントローラの装置記述ファイルを介して表示されます。

→ Value type を選択する。入力または出力の物理量または装置ステータスを設定します。
→ Default value を選択または非選択。

フィールドバスパートナー装置から信号が届かない場合、標準値が採用されます。

→ CANopen compatible を選択または非選択。

値が1台のCANopen装置によって消費される場合に選択されます。

→ Unit conversion を選択する。

PLCによって値が受信または送信される物理単位を決定します。

ゲートウェイ構成の入力と出力が選択・宣言されました。

→ Continue で、フィールドバス固有のアドレスマッピングのメニューを開きます。

26

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

10.4.3.3

フィールドバス固有のアドレスマッピング→ 編集可能なフィールドを確認し、必要に応じて入力します。

プロトコル固有の設定は、以下のスクリーンショットで説明しています。

→ Continue を選択します。
PROFINETのアドレスマッピング：
Create a gateway configuration

Profinet

Header info

Main family

Gateway

Device ID

0x23^

Information

Gateway

Device access point info^       Advanced
Module ID

0x100

Hardware version

A.01.01.00

Maximum input length

1400

Information

Gateway

Minimum cycle time of the gateway 4

Byte

Software version

580515

Maximum output length

1400

Compatible DNS name

MEX3

ms

Byte

Addressing
Automatic PROFINET addressing
Reset devices

Start

Slot and subslot description:These fields become ............

Assign module ID independently^       Advanced
Advanced table restore by loading the GSDML file
Cyclic

Back

Name

Index

Subindex Slot Subslot Subslot
index

Device status NamurNE107

0x2004 0x01

1

1

0

201

Control Word

0x3C32 0x01

2

1

0

202

CancelModuleID

GSDML slot
description

GSDML subslot
description

Continue

PROFINETアドレッシングの概要
Automatic PROFINET addressing
Start 自動PROFINETアドレッシングを再び実行します
Reset device：列5〜8の値を0にリセットします。
 GSDMLファイルをロードすることにより、既存のProfinetアドレッシングを復元できます。
フィールドバス固有の装置データとアクセスデータ
挿図 12：

ゲートウェイ構成; PROFINETのアドレスマッピング
27

日本語タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

EtherNet/IPのアドレスマッピング：
Create a gateway configuration

EtherNet/IP settings

EthernetIP Data

Major revision

Minor revision1

7

Order number
EtherNet/IP EDS revision
EtherNet/IP product code

EtherNet/IP product type Generic Device,keyable (43)

1.1

^

4300

Addressing
Automatic EtherNet/IP addressing
Reset devices

Start
Cyclic

Back

Name

Index

Subindex Assembly Connection Class (hex)

Device status NamurNE107

0x2004 0x01

0x66

2

0x66

0x01

0x03

Control Word

0x3C32 0x01

0x67

2

0x67

0x01

0x03

CancelContinue

EtherNet/IPアドレッシングの概要
Automatic EtherNet/IP addressing
Start 自動EtherNet/IPアドレッシングを再び実行します
Reset device：列5〜9の値を0にリセットします。
フィールドバス固有の装置データとアクセスデータ
挿図 13：

Instance (hex) Attribute(hex)

ゲートウェイ構成; EtherNet/IPのアドレスマッピング

28

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

ModbusTCPのアドレスマッピング：
Create a gateway configuration

Modbus TCP settings

Bus ident data
Device name:
Addressing
Automatic

Back

1.7

modbus TCP addressing

Coil/register addressing
CyclicMajorMinorRev

MEX3

^

Start

Name

Reset devices
Index

Start address 0

Use Modbus FC03 if possible

Start address 1

Subindex Size in Address Start
Function code
Bytes range
address

Device status NamurNE107

0x2004 0x01

1

1xxxx

0

Read:FC02

Control Word

0x3C32 0x01

4

4xxxx

0

Read:FC03, write single:FC06, write...

CancelContinue

Modbus TCPアドレッシングの概要
自動Modbus TCPアドレッシング
Start 自動Modbus TCPアドレッシングを再び実行します
Reset device：列5〜8の値を0にリセットします。
設定：
Coil/register addressing Register addressing：
Coil addressing：
コイルアドレッシングを設定できないコントローラーもあります。従って、レジスタアドレス
指定のみを使用することは合理的です。→次にスタートを押します
Use Modbus FC03 if possible：
フィールドバス固有の装置データとアクセスデータ
挿図 14：

ゲートウェイ構成; ModbusTCPのアドレスマッピング

29

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

EtherCATのアドレスマッピング：
Create a gateway configuration

EtherCAT

EtherCAT data

EtherCAT product code#xFDF9Product code of the EtherCAT device must be a whole number, e.g.:12345678

EtherCAT revision#x00010002

EtherCAT revision of the device must be an 8-digit hex number beginning with #x ....

Addressing
Automatic EtherCAT addressing
Start
CyclicBack

Reset devices
Name

Index

Subindex

Device status NamurNE107

0x20040x01

Control Word

0x3C320x01

CancelContinue

EtherCATアドレッシングの概要
Automatic EtherCAT addressing
Start 自動EtherCATアドレッシングを再び実行します
Reset device：値をリセットしますフィールドバス固有の装置データとアクセスデータ
挿図 15：

ゲートウェイ構成; EtherCATのアドレスマッピング

30

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

CCリンクIEフィールド・ベーシックのアドレスマッピング：
Create a gateway configuration

CC-Link IE Field Basic

Addressing

Automatic CC-Link addressing
Reset devices

Start
Cyclic

Back

Name

Index

Subindex

AI_AI10x25400x01

AI_AI20x2541

0x01

AI_AI30x25420x01

AI_AI40x25430x01

AI_AlasDI

0x25440x01

AI_NAMUR

0x25450x01

AI_DeviceStatusNamurNe107

0x20040x01

AI_DeviceSupplyVoltage

0x20040x03

AI_DeviceTemperature

0x20040x02

Start addressing

CancelContinue

CCリンクIEフィールドの基本的なアドレス指定の概要
自動CCリンクIEフィールドの基本的なアドレス指定
Start 自動CCリンクIEフィールドベーシックアドレッシングを再び実行します
Reset device：値をリセットします
挿図 16：

ゲートウェイ構成; CCリンクIEフィールド・ベーシックのアドレスマッピング

31

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

10.4.3.4

ゲートウェイ構成を保存します→ ダイアログボックスFinal settings で出力ディレクトリを選択します。
→ Continue を選択します。

ゲートウェイ構成が保存されます。
装置へのダウンロードはバックグラウンドで行われます。
指定したパスのサブフォルダには、既存の装置記述ファイルも含まれます。

→ Complete を選択します。
 装置の構成が完了しました。PLCとフィールドバスゲートウェイ間の接続が確立されます。記述ファイルを含む
フォルダが自動的に開きます。
以下の概要は、ゲートウェイの構成中に作成されるファイルを示しています。

ゲートウェイ構成ファイル

ストレージフォルダ

Description

Buerkert-Gateway-date-.bgc

フォルダなしゲートウェイの構成コンテナ

Buerkert-Gateway-Mapping-date-.xml

BGC

ゲートウェイマッピングファイル。
ファイルは自動的に装置にダウンロード
されます

Buerkert-Gateway-date-.eds

EDS

ゲートウェイ拡張ファイル。
ファイルは自動的に装置にダウンロード
されます

EtherCAT-Buerkert-Gateway-date-.xml

PLC_EtherCAT

装置記述ファイル。
オプション：PLCにインポートします

help_ethercat.csv

PLC_EtherCAT

周期的および非周期的な装置値の概要

EthernetIP-Buerkert-Gateway-date-.eds

PLC_EtherNetIP

装置記述ファイル。
PLCにインポートします

help_ethernetip.csv/txt

PLC_EtherNetIP

周期的および非周期的な装置値の概要

Connection-X-In/Out_Importdata.L5X

PLC_EtherNetIP

Rockwellユーザーのデータタイプ。すべてのアセンブリに使用されますModbusTCP-Buerkert-Gateway-date-.txt

PLC_ModbusTCP

装置記述ファイル

help_modbusTcp.csv/txt

PLC_ModbusTCP

周期的および非周期的な装置値の概要

GSDML-V2.32-Buerkert-Gateway-date-.xml

PLC_Profinet

装置記述ファイル。PLCにインポートします

GSDML-0078-0023-icon.bmp

PLC_Profinet

装置記述ファイルで使用されるアイコン。

help_profinet.csv/txt

PLC_Profinet

周期的および非周期的な装置値の概要。

プロトコルに依存しないファイル

EtherCATのファイル

EtherNet/IPのファイル

Modbus TCPのファイル

PROFINETのファイル

32

表 8：

ゲートウェイの構成中に作成されるファイルの概要

日本語

タイプ ME63
Bürkertコミュニケーターによるコミッショニ
ング

10.5

büSネットワーク構成→–

büS ナビゲーション領域で選択します。

→ 詳細ビュー Network configuration を 選択します。
COMMUNICATOR
File

Communication Edit

View

Options

Tools

büS

Help

Overview

Start page

Apply changes

Desktop
Graph–

MassFlowCo...

+

MassFlowController+

Gateway ME63

Discard changes

Gateway ME...

SensorbüS+–

Network Config

Modbus TCP

Actual value flow
Medium temperature
Totalizer

MFC01_ActualFl..
MFC01_NamurS
MFC01_Setpoint
MFC02_ActualFl..
MFC02_NamurS
MFC02_Setpoint
MFC03_ActualFl..
MFC03_NamurS
MFC03_Setpoint

Controller

Used set-point val...
Set-point value
Manual set-point
Actuator

Manual set-point
Other

NamurStatus100%

挿図 17：

Network Confi→ ドラッグ＆ドロップで入力と出力を接続します。

互換性のある接続点は青色で強調表示されます。
破線の接続は、
まだ装置間のアクティブな接続を確立していません。

→ Apply changes をクリックします。
構成されたすべての装置の再起動が実行されます。
büSネットワークが構成されました。

33

日本語

タイプ ME63
Webサーバーによるコミッショニング

11

WEBサーバーによるコミッショニング

FieldConnect タイプME63には、構成およびステータス情報の表示機能を提供するWebサーバーが統合されています。
Webサーバーの使用は、以下のプロトコルに対して可能です：• PROFINET• EtherNet/IP• Modbus TCP
Webサーバーからのアクセスには、装置のIPアドレスが使用されます。

注意
Webサーバーへの不正アクセス。
▶ 第三者による不正なアクセスを防ぐため、保護されたネットワーク内でのみ装置を操作してください。

11.1

Webサーバーの機能

Webサーバーを使用して、さまざまな設定（IPアドレスなど）を行うことができます。
Bürkertコミュニケーター (バージョン5.1以降) を使用して、ゲートウェイ構成が作成されている場合、Webサーバー
はシステム全体のイメージを表します。接続された装置が概要ページに表示されます。装置をクリックすると、装置
固有のページが表示されます。
Webサーバーには、
シリアル番号、装置タイプなどの基本データが表示されます。
さらに、ゲートウェイ構成中に宣言されたすべての循環データと非循環データが表示されます。
これは、各装置がWebサーバーアクセス中に、ゲー
トウェイにも接続され、büSマッピングにより接続されている場合にのみ機能します。
アクセス中に装置が使用できない場合、割り当てられた装置IDのギャップがWebサーバーに残ります。

11.2

Bürkertコミュニケーターを介してWebサーバーを有効化する

ウェブサーバーは、Bürkertコミュニケーターによって、有効化または無効化できます。
Web server > Parameter > Activate web server

11.3

ウェブサーバーへの接続を確立する→ ネットワークケーブルを介してPCを装置と接続します。
→ ウェブブラウザのアドレスバーにIPアドレスを入力します。
装置のデフォルトIPアドレスは、192.168.0.100です。
IPアドレスが不明な値に変更された場合、装置の現在のIPアドレスをビュルケルトコミュニケーターで判定することができます。
複数の装置の構成：
出荷時、すべての装置は次の同じIPアドレスを持っています。192.168.0.100。装置が構成のために識別されるには、
ネットワークにまだ構成されていない装置が1台だけ存在する必要があります。
▶ 装置を順に1つずつネットワークと接続して構成します。

34

日本語

タイプ ME63
Webサーバーによるコミッショニング

挿図 18：

ウェブサーバーのビュー

11.4

Webサーバーでログインする→ スタートページの左上にある Login をクリックします。
→ ユーザー名とパスワードを入力します： ーザー名：admin
ユ
パスワード：admin（またはMAC address）→ Login をクリックします。

挿図 19：

Webサーバーでログインする

35

日本語

タイプ ME63
Webサーバーによるコミッショニング

11.5

パスワード

注意
標準パスワードに基づくセキュリティリスク。
権限のない第三者がWebサーバーでログインし、システムで変更を行うことができます。
► 標準パスワードを変更します。
► Webサーバーが必要ない場合は、
Bürkertコミュニケーター経由のアクセスを無効化します。

Web server > Parameters > Deactivate web server。

以下のユーザー名とパスワードは標準で有効になっており、パスワードのリセット時に再び有効になります。
製造日

2020年12月まで

2021年1月より

ユーザー名

admin

admin

標準パスワード

admin

MACアドレス

MAC addressは、装置とBürkertコミュニケーターに表示されます。
(Protocol name) > Parameters > (Protocol name) settings > MAC address
MAC addressの正しい入力（例）：DC-B0-58-00-15-D6
MAC addressのパスワードを入力する際は、「-」が正しく書かれていることを確認してください。

11.5.1

パスワードを変更する→ Webサーバーでログインします。
→ メニュー General settings で新しいパスワードを入力し、確定します。
11.5.2

パスワードを工場出荷時設定にリセットする→ Login をクリックします。
→ ログインウィンドウの右下にあるパスワードの Reset をクリックします。
パスワードを実際にリセットするためには、装置で3分以内に再起動を行う必要があります。再起動は、
フィールド
バスゲートウェイのディスプレイ、
ソフトウェア「Bürkertコミュニケーター」、
または電圧リセットによって行うことが
できます。

11.6

装置構成
複数の装置の構成：
装置は工場出荷状態で同じIPアドレスを持っているため、装置を同定できるようにするためには、ネットワ
ーク内にまだ未設定の装置が1つ以上存在してはいけません。
▶ 装置を順に1つずつネットワークと接続して構成します。

→ 装置の名称とIPアドレスを入力します。

装置名(DNS互換名)は、構成時に使用されます。

→ Apply をクリックします。
変更されたパラメータを適用するには、装置の電圧リセットが必要です。

→ 製品を再起動します。
36

日本語

タイプ ME63
OPC UA

12

OPC UA

12.1

一般的な説明OPC UAサーバーは、OPC UAクライアントにゲートウェイ構成によって決定された値（循環および非循環）を読み書きするオプションを提供します。
ME63および接続されているbüS装置のデータをOPC UAクライアントで使用できるようにするには、次の点に注意する必要があります：• Bürkertコミュニケーターのバージョンが6以上のゲートウェイ構成を実行する必要があります。非周期的な値も選択できます。
• 設定されたプロトコルによって、コントローラーとOPCクライアントを使用できる値は同一であり、個別に表示することはできません。
• ゲートウェイの構成後、büSマッピングを実行する必要があります。büS装置がマッピングにより、ゲートウェイに接続されていない場合、装置の値と名称を読み取ることはできません。

12.2

OPC UAとの接続の確立

サーバーOPC UAの機能の有効化と無効化は、Bürkertコミュニケーターで設定します。
OPC UA > Parameter > Enable OPC UA

OPC UA
Parameter

Maintenance

Enable OPC UA

挿図 20：

オフ

OPC UA、有効化

OPC UAの有効化の後、OPC UAサーバーの詳細設定が表示されます。

12.2.1

装置の設定

IPパラメータは、プロトコル固有の設定で設定されます。
詳細ビュー

メニュー

Parameter

Enable OPC UA

OPC UAは、
ここで有効化または無効化できます。
この設定は、次に装置を再起動したときに有効になります

Server port

OPC UA通信用ポートの設定。納品状態：4840

Number of objects
being monitored

OPC UAサーバーがモニターする最大数を制限するのに使用します

Event typeME63のイベントをどのタイプで送信するかを設定します。接続された
büS装置からイベントを送信できるようにするには、
General settings > System monitoring > Diagnostics で、対応するタイプを選択する必要があります

表 9：ME63 (OPC UAサーバー)の設定
37

日本語

タイプ ME63
OPC UA

設定を変更した後、装置を再起動する必要があります。

12.2.2OPC UAクライアントの設定

エンドポイントURL

opc.tcp://*ME63のIPアドレス*:*サーバーポートを設定します (工場出荷時設定：4840)*
例：opc.tcp://192.186.0.100:4840

セキュリティ設定
セキュリティポリシー

なし

メッセージセキュリティモード

なし

認証設定

匿名

12.3

サーバー証明書

OPC UAサーバーは、ファクトリーサーバー証明書を自分のものと交換するオプションをユーザーに提供します。交換は、Webサーバー経由で実行できます。
証明書の発行：→ ME63のIPアドレスでWebサーバーを開きます。
証明書は、ログイン後にのみ変更できます。

→ OPC UA Server を選択します。
→ Server certificate の下のアイコンをクリックして、「DER」型式のファイルを選択します。

→ Change certificate を選択します。

38

挿図 21：

サーバー証明書の変更

日本語

タイプ ME63
OPC UA

転送が成功したら、装置を再起動する必要があります。
ユーザー固有の証明書を削除し、工場出荷時の証明書を有効化します。

→ Change certificate をクリックします。
→ Ok で確定します。
再起動後、ファクトリー証明書がロードされます。
工場出荷時設定にリセットすると、ユーザー固有の証明書が削除され、工場出荷時の証明書が有効になります。
ユーザー固有の証明書は、リムーバブルストレージ装置に保存されないので、構成が別の装置の転送されるときに転送されません。

39

日本語

タイプ ME63
ディスプレイエレメント

13

ディスプレイエレメント

タイプME63には、装置のステータスを診断するための次のLEDがあります：• バスステータス（通信状態）を表示するためのLED。
• 装置ステータスを表示するためのLED

LED装置状態

バスステータスLED2(通信状態)

バスステータスLED1(通信状態)

Link/Act

Link/Act

挿図 22：

タイプME63の表示要素

13.1

バスステータスを表示するためのLED

分離状態表示が欠くバスステータスに割り当てられています（通信状態）。緑から赤によって、通信状態の変なkを表示するためのLED。

13.1.1PROFINET IO

LED

カラー

LEDバスステータス1(システムエラー)

2個のLED赤/緑

LEDバスステータス2(バスエラー)

Link/Act

Link/Act

表 10：

状態

Description

オフ

オフ

エラーなし

赤

点滅

DCP信号サービスがバスによってトリガーされた

赤オン

ウォッチドッグタイムアウト、延長診断可能、
システムエラー

2個のLED赤/緑
オフ

オフ

エラーなし

赤

点滅

データ交換なし

赤オン

構成なし、物理接続遅延またはなし

緑オン

装置がEthernetと接続している

オフ

オフ

装置がEthernetと接続していない

黄点滅

装置がEthernetフレームを送信/受信している

オフ

オフ

装置がEthernetフレームを送信/受信していない

緑LED

黄LED

LEDの説明、PROFINET IO

40

日本語

タイプ ME63
ディスプレイエレメント

13.1.2
LED

EtherNet/IP
カラー

状態

LEDバスステータス1 2個のLED赤/緑(モジュール状態)
緑オン

Description
装置稼働中：装置が稼働しており、正しく動作している

緑点滅

スタンバイ：装置が未設定です

緑-赤-赤

点滅

セルフテスト：装置がパワーオンテストを実行しています。
モジュールステータス表示のテストシーケンスは、次のシーケンスに従って、ネットワークステータス表示のテストシー
ケンスの前に実行されます：• ネットワークステータスLED消灯• モジュールステータスLEDは、約250ミリ秒間、緑に点灯し、約250ミリ秒間赤に変わり、再び緑に点灯します（テストが完了するまでこの状態を維持します）• ネットワークステータスLEDは、約250ミリ秒間、緑に点灯し、約250ミリ秒間赤に変わり、そのご消灯します（テストが完了するまでこの状態を維持します）

赤点滅

致命的な回復可能エラー：装置に致命的な回復可能エラーが発生しました。例えば、不正または一貫性のない構成などは、修復が困難なエラーに分類されます赤オン

致命的な回復不能エラー：装置に致命的な回復不能エラーが発
生しました

オフ

オフ

電源断：装置の電源が切れた

LEDバスステータス2 2個のLED赤/緑(ネットワーク状態)
緑オン

緑Link/Act

Link/Act

表 11：

点滅

接続済み：IPアドレスが構成され、（任意のトランスポートクラスの）少なくとも1つのCIP接続が確立され、排他的オーナー接続はタイムアウトしていません
接続なし：IPアドレスが構成されていますが、CIP接続が確立されておらず、排他的オーナー接続がタイムアウトしていません

緑-赤-消灯 点滅

セルフテスト：装置がパワーオンテストを実行しています赤点滅

接続タイムアウト：IPアドレスが構成され、この装置を対象とする
排他的オーナー接続がタイムアウトしました。
制限時間を超えたすべての排他的オーナー接続が復旧した場合にだけ、ネットワークステータス表示が永続的に緑にリセットされ
ます。

赤

オン

IPの重複：装置はそのIPアドレスがすでに使用されていると判断
しました

オフ

オフ

スイッチオフ、IPアドレスなし：装置にIPアドレスがありません（またはスイッチがオフになっています）

緑

オン

装置がEthernetと接続している

オフ

オフ

装置がEthernetと接続していない

黄点滅

装置がEthernetフレームを送信/受信している

オフ

オフ

装置がEthernetフレームを送信/受信していない

緑LED

黄LED

LEDの説明、Ethernet/IP

41

日本語

タイプ ME63
ディスプレイエレメント

13.1.3
LED

Modbus TCP
カラー

状態

LEDバスステータス1 2個のLED赤/緑
(Run)
緑
オン

Link/Act

表 12：

接続済み：OMBタスクに通信があります。少なくとも1つのTCP接続が確立されています緑

点滅

レディ状態ですが、未設定です：OMBタスクはレディ状態ですが、まだ未設定です緑点滅

通信待機中：OMBタスクが構成されています

オフ

オフ

レディ状態ではありません：OMBタスクがレディ状態ではありません

LEDバスステータス2 2個のLED赤/緑
(エラー)
オフ
オフ

Link/Act

Description

通信エラーなし

赤点滅

システムエラー

赤オン

通信エラーアクティブ

緑オン

装置がEthernetと接続している

オフ

オフ

装置がEthernetと接続していない

黄点滅

装置がEthernetフレームを送信/受信している

オフ

オフ

装置がEthernetフレームを送信/受信していない

緑LED

黄LED

LEDの説明、Modbus TCP

42

日本語

タイプ ME63
ディスプレイエレメント

13.1.4
LED

EtherCAT
カラー

状態

LEDバスステータス1 2個のLED赤/緑
(Run)
オフ
オフ

Description
装置はINIT状態です

緑点滅

装置はプレオペレーション状態にあります（運転前）

緑

点滅のみ

装置はセーフオペレーション状態にあります（安全運転中）

緑

オン

装置はオペレーション状態にあります（運転中）

LEDバスステータス2 2個のLED赤/緑
(エラー)
オフ
オフ
赤

点滅

エラーなし：装置のEtherCAT通信が稼働しています
無効な構成：一般構成エラー
考えられる原因：レジスタまたはオブジェクトの設定により、マスターが指定したスタータス変更はできません。

赤

点滅のみ

ローカルエラー：スレーブ装置アプリケーションは、EtherCAT
ステータスを単独で変更しました
考えられる原因：- ホストウォッチドッグタイムアウトが発生した- 同期エラー、装置は自動的にセーフオペレーションに切り替
わります。

赤

2回点滅

プロセスデータウォッチドッグ：プロセスデータウォッチドッグ
タイムアウトが発生しました
考えられる原因：Sync-マネージャー-ウォッチドッグ-タイムア
ウトLink/Act

Link/Act

緑LED
緑

オン

装置はEthernetに接続されており、Ethernetフレームを送受信していません緑点滅

装置はEthernetに接続されており、Ethernetフレームを送受信
しています

オフ

オフ

装置がEthernetと接続していない

オフ

LEDは使用していません

黄LED
オフ

表 13：

LEDの説明、EtherCAT

43

日本語

タイプ ME63
ディスプレイエレメント

13.1.5

CC-Link IE field basic

LED

カラー

Run

2個のLED赤/緑

Error

Link/Act

Link/Act

Description

緑オン

ステーションが稼働しており、周期的通信を実行中です緑点滅

ステーションが稼働していますが、周期的通信は停止してい
ます

緑

点滅

ステーションが未設定ですオフ

オフ

ステーションが分離されています

2個のLED赤/緑
赤

オン

通信エラー

赤

3回点滅

DPMウォッチドッグがタイムアウトしましたオフ

オフ

ステーションが分離されています

緑オン

リンク：ステーションはEthernetに接続されており、Ethernet
フレームを送受信していません

緑点滅

アクティビティ：ステーションはEthernetに接続されており、Ethernetフレームを送受信しています

オフ

オフ

ステーションがEthernetと接続していない

オフ

LEDは使用していません

緑LED

黄LED
オフ

表 14：

状態

LEDの説明、CCリンクIEフィールド・ベーシック

44

日本語

タイプ ME63
ディスプレイエレメント

13.2

装置ステータス表示用LED

NAMUR NE 107に基づいて、装置ステータスを表示するLEDが色とステータスを変更します。
複数の装置ステータスが同時に存在する場合は、最も優先度の高い装置ステータスが表示されます。優先度は、標準操作からの偏差の重大度に依存します（赤色=故障=最高優先度）。
NAMURモードでの表示：
NE 107に基づいた表示

Device status

意味

カラーコード カラー
5

赤

故障、エラーま
たは障害

誤動作。製品の機能は保証されません。

4

オレンジ

機能チェック

装置は、büSフィールドパティシパントを検索します。
このステータスは数秒後に終了します。
装置シミュレーションがアクティブです。

3

黄

仕様外

周囲条件またはプロセス条件が、指定された範囲外です。
製品内診断は、製品またはプロセスプロパティの問題を示します。
データシート値を遵守することはできません。

2

青メンテナンス要件

装置は進行中の診断を通じて偏差を検出し、訂正を行いました。

→ 装置をメンテナンスします。

装置構成を管理 更新された製品構成を保存できません。
できません
製品を交換すると、構成を転送できません。
1

緑診断がアクティブ

製品にエラーが発生していません。
ステータスの変更は色で表示されます。
メッセージは、必要に応じて接続されたフィールドバスを介して送信されます。

0白診断が非アクティブ

製品がオンになっています。
ステータスの状態は表示されません。
メッセージはメッセージリストにリストされていないか、または接続されているフィールドバス経由で送信されます。
装置は仕様内で作動します。

表 15：

NAMURモードでの装置状態の表示

45

日本語

タイプ ME63
Bürkertコミュニケーターメニュー

14BÜRKERTコミュニケーターメニュー

次の概要では、Bürkertコミュニケーターソフトウェアを使用したタイプ ME63の装置固有の設定について、説明します。
ソフトウェアの基本的な操作については、説明していません。
Bürkertコミュニケーターソフトウェアの使用に関する詳細情報は、ビュルケルトホームページ(http://country.burkert.com → 8920 →「取扱説明書」のダウンロード)にあります。
次の概要は、「インストーラー」ユーザーレベルで表示されるメニューを示しています。
このユーザーレベルには、最高レベルの権限があります。

14.1「ウェブサーバー」および「OPC UA」構成範囲

WebさーばーとOPC UAのメニューは、次のプロトコルでのみ表示されます：• PROFINET IO• EtherNet/IP• Modbus TCP
Webサーバーを有効または無効にします：
Web server > Parameter > Activate web server
OPC UAサーバーを有効または無効にします：
OPC UA > Parameter > Enable OPC UA

46

日本語

タイプ ME63
Bürkertコミュニケーターメニュー

14.2

構成範囲「PROFINET」、「EtherNet/IP」、「Modbus TCP」およびCCリンク
IEフィールド・ベーシックのメニュー

パラメータ詳細ビュー
詳細ビュー

メニュー

Parameter

PROFINET, EtherNet/IP,
Modbus TCP or CC-Link IE
field basic settings

Wizard büS通信の入力チェックおよび開始条件のために設定します。
IP parameter settings
Set DNS compatible name。
Set Fixed IP address。
Set Network mask。
Set Standard gateway。
Temporary IP address を指定します。
MAC address が表示されます。
Advanced settings

Alarm settings
Internal cycle time
Control mode settings
Firmware update protocol

Gateway configuration

Download a gateway configuration file
Create a gateway configuration

Unit conversion
Hide process values

Edit values to be hidden
Reset hidden values

Acyclic routing settings
Change protocol
表 16：

Protocol の選択「PROFINET」構成範囲の設定、パラメータ詳細ビュー

詳細ビュー「診断」
詳細ビュー

メニュー

Diagnostics

Configuration file information
これらのメニューでは、現在の値が設定されずに表示されます。

ProtocolCommunication status
Established connections to PLC
Current internal cycle time
Advanced
表 17：

Last status code

「PROFINET」構成範囲の設定 診断詳細ビュー

47

日本語

タイプ ME63
Bürkertコミュニケーターメニュー

メンテナンス詳細ビュー
詳細ビュー

メニュー

MaintenanceVersion numbers

これらのメニューでは、現在の値が設定されずに表示されます。

Stack name
Stack version
Stack build
Stack revision
Stack date
ICom version

Hardware reset of industrial
communication
表 18：「PROFINET」構成範囲の設定 メンテナンス詳細ビュー

14.3「EtherCAT」構成範囲のメニュー

パラメータ詳細ビュー
詳細ビュー

メニュー

Parameter

EtherCAT settings

Wizard büS通信の入力チェックおよび開始条件のために設定します。
Station alias
MAC address が表示されます。
Advanced settings

Alarm settings
Internal cycle time
Control mode settings
Firmware update protocol

Gateway configuration

Download a gateway configuration file
Create a gateway configuration

Unit conversion
Hide process values

Edit values to be hidden
Reset hidden values

Acyclic routing settings
Protocol の選択

Change protocol
表 19：「EtherCAT」構成範囲の設定、パラメータ詳細ビュー

48

日本語

タイプ ME63
Bürkertコミュニケーターメニュー

14.4「一般設定」構成範囲のメニュー

パラメータ詳細ビュー
詳細ビュー

メニュー

Parameter

Status LED

Set operation mode

büS

büSインターフェースの構成
Assign displayed name をディスプレイとBürkertコミュニケーターに割り当てます。
Location 装置に表示される場所を指定します。
Description ツールヒントの説明テキストを入力します
Advanced

Unique device name パートナーの割り当て。
Baud rate を指定します。
CANopen address を指定します。
Bus mode büSインターフェースのモードを設定しますShow errors from büS partners フィールドバスパー
トナーエラーを表示するかどうか、またはエラーを表示パートナーを設定します。
Deallocation delay フィールドバスパートナーを失ってから構成を削除するまでの時間。

Alarm limits

装置が警告またはエラーを発行する制限を設定します。
Supply voltage 供給電圧のアラーム制限を設定します。
Device temperature 装置温度のアラーム制限を設定します。
Warning of battery voltage below 値の表示。

Diagnostics

診断を有効または無効にします。

PDOconfiguration プロセスデータオブジェクトの構成
PDO 1
Reset to default values
Configuration
providerStatus 構成プロバイダを有効または無効にします。
Remove all device configurations 装置の再起動後に動作を設定します。
Forced reconfiguration of all devices 装置の再起動後に動作を設定します。
Ignore offline devices 有効または無効にします。

Systemmonitoring

表 20：

Diagnostics
Individual diagnostics of the system devices

構成範囲「一般設定」の設定 パラメータ詳細ビュー

49

日本語

タイプ ME63
Bürkertコミュニケーターメニュー

詳細ビュー「診断」
詳細ビュー

メニュー

Diagnostics

Device status

Operating duration
Device temperature
Supply voltage
Voltage drops 再起動後以降の数。
Min./Max. values

これらのメニュー
では、現在の値が設定されずに表示されます。

Max. temperature
Min. temperature
Max. Supply voltage
Min. Supply voltage

Device start counter
Removable storage medium status
Current system time
Battery voltage
büS status

Receive errors 再起動後以降の数。
Max. receive errors 装置状態に達した最も重大な受信エラーが表示されます。
ディスプレイは0にリセットできます。
Send errors 再起動後以降の数。
Max. send errors 装置状態に達した最も重大な送信エラーが表示されます。
ディスプレイは0にリセットできます。
Reset error counter
CANopen status 稼働中または稼働準備中

Logbook                ログブックには、タイプ、時刻および署名を含むすべての警告とエラーメッ
セージが一覧表示されます。
ログブックに表示されるメッセージは、更新、保存および削除することができます。
Configuration
providerStatusNumber of managed devices– Number of which offline configurations– Number of which authorised reconfigurations
Number of reconfigured devices
Number of loaded device configurations
Number of missing devices
Number of faulty configuration load processe（再起動以後）s
Number of faulty reconfigurations
Removable storage medium status

表 21：

50

「一般設定」構成範囲の設定 診断詳細ビュー

メンテナンス詳細ビュー

日本語

これらのメニュー
では、現在の値が設定されずに表示されます。

タイプ ME63
Bürkertコミュニケーターメニュー

詳細ビュー

設定

MaintenanceDevice information

Displayed name 情報ビュー（パラメータ）の同じ名前のメニューに名前が入力されている場合にのみ表示されます。
Identification number

これらのメニュー
では、現在の値が設定されずに表示されます。

Serial number
Software ident. number
Software version
büS version
Hardware version
Product type
Manufacturing dateeds version
f(x) version
Device driver

Driver version
Firmware group
DLL version
Place of origin

Reset device

RestartFactory reset

表 22：

構成範囲「一般設定」のメニュー、詳細ビュー「メンテナンス」

51

日本語

タイプ ME63
トラブルシューティング

15

トラブルシューティング

問題

考えられる原因

処置

NAMUR-LEDが定期的に消灯する。

電力供給が定期的に切れ、製品が毎回リセットを実行する。

十分な電力のある電源を使用してください。

接続ケーブルの電圧降下が大きすぎる。

ケーブルの断面積を増やします。

産業用イーサネットとbüS間で ケーブルが接続されていない
プロセス値が転送されない。

ケーブルの長さを短くしてください。
EthernetとbüSケーブルを確認してください。

値の読み取りと書き込みが装置の制御オブジェクトのPLCによって認可されない。

装置の制御オブジェクトの値の読み取りと書き込みを有効にします。

プロセス値が正しく構成されていな
い。

プロセス値の構成を確認してください。

プロセス値が正しく割り当てられていない。

büSフィールドバスパティシパントへのプロセス値の割り当てを確認してください。

プロセス値をbüSフィールドバ プロセス値が未設定です。
プロセス値の構成を確認してください。
スパティシパントに割り当てる 構成適用の完了後に製品を再起動し 構成後に製品を再起動します。
ことができない。
ていない。

誤った値が送信されるか値がゼロである。

プロセス値が異なるクラスに割り当てられている。

büS フィールドバスパティシパントが同じクラスのプロセス値であるか割り当てを確認してください。

入力方向と出力方向の割り当てが遵守されていない。

入力方向と出力方向が正しいことを確認してください。

プロセス値が割り当てられていない プロセス値の割り当てを確認してくだか間違ったフィールドバスパティシパ さい。
ントに割り当てられている。

故障した装置からのmicroSD 交換装置と故障した装置の装置ソフ 同じIDを持つ装置間でのみ値を転送でカードの値が交換装置に適用 トウェアID番号が異なっている。
きます。
されない。
microSDカードに欠陥がある。装置が microSDカードを交換し、故障した装置
microSDカードに値を書き込むことのパラメータをmicroSDカードに再度ができない。
転送してみてください。
故障した装置からのmicroSD 交換装置と故障した装置のEDS装置 故障した装置の既存の値のみ交換装置
カードのすべての値が交換装 説明が異なっている。
に転送できます。交換装置の新しい値
置に適用されない。
は、
ソフトウェア「Bürkertコミュニケータ
ー」を使用してパラメータ化する必要が
あります。
表 23：

トラブルシューティング

52

日本語

タイプ ME63
トラブルシューティング

15.1

エラーコードの説明

エラーコード Description
1／3

過負荷検出。

2／1

過電圧検出。

2／2

低電圧検出。

2／3

電圧警告制限の超過。

2／4

電圧警告制限未満。

2／5

バッテリー電圧警告制限未満。

2／6

電圧ディップ検出。

3／1

過剰温度検出。

3／2

過少温度検出。

3／3

温度警告制限の超過。

3／4

温度警告制限未満。

18／4

SDカードの欠陥。

18／7

リムーバブルストレージ利用可能。

18／8

リムーバブルストレージへのアクセス不可。

18／9

別の装置で構成を正常に管理。

18／10

別の装置で構成の管理不可。

18／11

構成プロバイダで装置構成のロード不可。

18／12

少なくとも1台の装置が欠落。

18／13

Bürkertコミュニケーター必要。

18／14

装置交換必要。

18／15

オプションが多すぎて装置交換不可。互換性のある装置数を削減。

18／16

装置交換での問題。

18／17

装置交換での問題。少なくとも1つのオブジェクトの書き込み不可。

18／18

装置交換失敗。

18／19

装置交換正常。

18／20

メモリカード不検出により構成プロバイダが非アクティブ。

18／21

複数の構成プロバイダがアクティブ！他のプロバイダ機能をオフにします。

32／1

内部メッセージ保管の容量超過。

32／130装置の初期化。

33／1「操作」状態に変更。

33／2「診断アクティブ」状態に変更。

33／3「メンテナンス」状態に変更。

33／4「仕様外」状態に変更。

33／5「機能点検」状態に変更。

33／6「エラー」状態に変更。

33／7

動作状態自動に変更。

33／8

操作モードを手動に変更。

33／9

特別モードに変更：LED点滅。

53

日本語

タイプ ME63
トラブルシューティング

エラーコード Description
33／11「オフ」状態に変更。

33／12

少なくとも1つの値に対して入力値シミュレーションがアクティブ。

33／13

少なくとも1つの値に対して出力値シミュレーションがアクティブ。

33／14

デモモードがオン。

33/32768

1件のステータスメッセージ保留中。

35／1

EERPROMエラー検出。

35／2

少なくとも1つの永続メモリが使用不可。

40／996

1つ以上のフィールドバスパートナー装置でエラー発生。

45/256büSイベント：büS動作なし。

45／257büSイベント：通信の初期化。

45／512büSイベント：ローカライズ。

45／768büSイベント：装置は同じアドレスを使用。

45/1024büSイベント：バス接続不明/利用不可。

45／1792büSイベント：フィールドバスパートナー検索アクティブ。

45／1793büSイベント：メーカー未検出。

45／1794büSイベント：アドレスなしの手動構成装置。検索最長1分。

45／1795

büSイベント：メーカーの割り当て不適切。

45／1796büSイベント：メーカー削除失敗。

45／1797büSイベント：不適切なCANopen構成装置。

45／1798büSイベント：両方のbüSインターフェースでGCVを設定。

45／1799büSイベント：メーカーの周期的通信が非アクティブ。

45／2048büSイベント：永続的なbüSデータを保存（装置の電源は切らないこと）。

45／2049büSイベント：永続的なbüSデータを削除（装置の電源は切らないこと）。

45／2304büSイベント：非周期データのルーターがアクティブ。

45／2560büSイベント：不適切なシリアル番号。

45／2561büSイベント：周期的な入力の構成が不適切（フィルターが不十分）。

45／2562büSイベント：周期的な値の構成が不適切。

45／2816büSイベント：マネージャがアクティブ。

45／3072büSイベント：監視対象装置に障害発生。

45／3584

アドレッシングの待機。

45／4096

装置パラメータの初期化エラー。

45／4097

設定アドレスはすでに使用済み。

51／1

プロセス制御システムへの接続が不適切。

51／2

周期的なデータトラフィックが設定されたタイムアウトパラメータよりも低速。

51／10

産業用通信の初期化。

51／101

NetX構成のエラー（ファームウェアのダウンロード中など）。

51／102

産業用通信がオフ。

51／103

マッピングファイルが存在しないか不適切。

51／104

利用可能なプロトコルファームウェアなし。

54

日本語

タイプ ME63
トラブルシューティング

エラーコード Description
51／105プロトコルを選択して装置を再起動。

51／201プロトコルスタックの初期化エラー。

51／202プロトコルスタックの構成エラー。

51／203

MACアドレスの送信エラー。

51／204

オブジェクトデータの登録エラー。

51／205接続の登録エラー、5つ以上指定。

51／206

間違ったPROFIBUSアドレス、
アドレス1～126のみ可能。

51／207

不正なCC-Linkリンクアドレス、
アドレス1～64のみ可能。

51／208

間違ったCCリンクボーレート。

51/300

フィールドバスマスターが停止状態。

51／303周期的なデータ交換中のエラー。

51／400

マスターが故障しているモジュール/サブモジュールの接続を試行。

52/3

機能ペイロードのCRCエラー、再構成必要。

52／4

機能生成不可（機能が不明？）。

52／5

機能の初期化不可。

52/7

機能番号が無効、再構成必要。

52／10

f(x)のペイロードキャッシュがフル、機能数またはプログラムのサイズを削減する。

52／11

機能計算エラー。

52／12

ユーザーメッセージ。

52／13

指定したサイクルタイムよりも長く計算された機能が無効化！必要に応じてサイクル時間を増
やす。

52／15

グラフィック f(x)プログラムのサイクル時間が関連する機能のサイクル時間と不一致。装置にプログラムを再ロードする。

52/18

グラフィカルプログラムエディター：プログラムが読み込まれていない、装置にプログラムを読
み込む。

52/21

グラフィカルプログラムエディター：プログラムのライセンスが不十分！全機能のロックを解除す
るには、Bürkert販売店にお問い合わせください！

52／22

グラフィカルプログラムエディター：無効な永続データ！デフォルト値を使用。

52／23

グラフィカルプログラムエディター：プログラムとプログラム構成が不一致、再構成必要。

52／24

グラフィカルプログラムエディター：ライセンスなし。1時間のプログラム実行後に非アクティ
ブ化。

52／25

グラフィカルプログラムエディター：ライセンスなし。
プログラム終了！全機能のロックを解除するには、Bürkert販売店にお問い合わせください！

63/10

少なくとも1個のbüS装置が、次のステータスになっています：メンテナンス。

63／11

少なくとも1個のbüS装置が、次のステータスになっています：仕様外。

63／12

少なくとも1個のbüS装置が、次のステータスになっています：機能テスト。

63／13

少なくとも1個のbüS装置が、次のステータスになっています：エラー

表 24：

エラーコードの説明

55

日本語タイプ ME63
トラブルシューティング

16

アクセサリ

16.1

パッシブディストリビューター

パッシブディストリビューターは、büSネットワークをケーブル接続するためのタイプME63のアクセサリとして使用できます。パッシブディストリビューターには、センサーまたはアクチュエータを接続するための9個のコネクター（X1～X8、場合によりX02）があります。

LED装置状態
カバーリッドの下：供給電圧を接続X03（Lコード）から、接続X01（Aコード）に切り替えるた
めのスイッチ。

接続X01+X02、Aコード

納品状態：接続X03有効
接続X03+X04、Lコード

挿図 23：

パッシブディストリビューター

出力に電力が供給されると、装置ステータスLEDが緑に点灯します。

16.1.1

テクニカルデータ注意
高温と多量の霜による機能障害。
▶ 指定された環境温度の範囲外では装置を使用しないでください。
周囲温度–20～+60 °C

使用高度

海抜 2000 m まで

ハウジングの寸法

65 mm x 210 mm x 18 mm (B x H x T)

素材

ハウジング：ポリカーボネート
ナチュラル
ポッティング：WEVOPUR 552 FL、

56

日本語

タイプ ME63
トラブルシューティング

16.1.2

電気データ

注意▶ 電源がLコード接続を使用している場合は、4 AのAコード接続の最大電流負荷を観察します。
供給電圧

24 V

消費電力

センサ/アクチュエータの電源供給は1接続部 (X1〜X8) あたり4 Aに制限されて
います。

最大電力

すべての出力で32A//740W

保護等級

IP65/67 (接続に保護キャップ装着されている場合のみ)

UL製品

UL認証過電流保護付きSELV/PELV、UL/IEC 61010-1 表18に準拠した設計

保護クラス

DIN EN 61140 (VDE 0140)準拠の3

16.1.3±10%

サイドリッドを開閉する→ サイドリッドを開閉するには、＋ドライバーで、2本のネジを緩めるか、ねじ込みます。
注意
リッドをネジで固定する際、保護等級を確認してください。
► シーリング材が正しく取り付けられているか点検します。
► リッドをネジで締めるする際、最大締め付けトルク0.4 Nmを順守してください。

16.1.4接続の割り当て注意
保護等級を確保します。
► 使用していない接続部に保護キャップを装着してください。

接続X03、X04

FE

FE

1

4

4

1

2

3       3

2

ピン

割り当て

機能

1

24 V

電源

2

GND

電源

3

GND

電源

4

(24 V)

電源

5

FE

シールド

パッシブディストリビューターM12、X03 (プラグ)、X04 (ソケット)、Lコード

表 25：

接続 X1-X8およびX01+X02

4
1

表 26：

5

3

3

2         2

5

4
1

ピン

割り当て

機能

1

FE/CAN_GND

シールド

2

24 V

電源

3

GND

電源

4

CAN_H

büS通信

5

CAN_L

büS通信

パッシブディストリビューター、接続 M12、X01 (プラグ) およびX1～X8 およびX02 (ソケット)、Aコード

日本語

57

タイプ ME63
トラブルシューティング

16.2

büSアクセサリ注意
誤った部品による物的損害
誤ったアクセサリや不適切なスペアパーツは、製品を損傷する恐れがあります。
▶ Bürkertの純正アクセサリと純正スペアパーツのみ使用してください。
アクセサリ

Order number

USB-büSインターフェースセット1（アダプタ、büSスティック、終端抵抗、Yディストリビュータ、M12プラグ付き
0.7 m接続ケーブルを含む）

00772426

USB-büSインターフェースセット2（büSスティック、終端抵抗、Yディストリビュータ、M12プラグ付き0.7 m接続ケーブルを含む）00772551

表 27：

アクセサリ

58

日本語

タイプ ME63
保管

17

保管

注意
誤った保管は装置の損傷の原因となります。
▶ 装置は乾燥した清潔な場所に保管してください！
▶ 保管温度 –20～+70 °C.    

18

廃棄処分

注意
媒体汚染された部品による環境への被害。
▶ 環境に配慮した方法で製品と梱包材を廃棄処分してください！
▶ 該当する廃棄規則および環境規制を遵守してください。

各国の廃棄物処理規則に従ってください。

59

日本語

www.burkert.com