137945_Rev_F 7.29.10

Jøtul GF 300 BV Allagash

Natural Vent Gas Stove

Installation andOperation Instructions
WARNING: If the information in these
instructions is not followed exactly, a fireor explosion may result causing property
damage, personal injury or loss of life.
– Do not store or use gasoline or otherflammable vapors and liquids in the vicinityof this or any other appliance.
– WHAT TO DO IF YOU SMELL GAS• Do not try to light any appliance.

• Do not touch any electrical switch; do not
use any phone in your building.

• Immediately call your gas supplier from aneighbor’s phone. Follow the gas supplier’s
instructions.
• If you cannot reach your gas supplier, callthe fire department.

– Installation and service must be performed
by a qualified installer, service agency or thegas supplier.
– In the Commonwealth of Massachusetts,
a carbon monoxide (CO) detector shall be
installed in the same room as the appliance.

This appliance may be installed in an aftermarket,
permanently located, manufactured home or mobile
home, where not prohibited by local codes.
This appliance is only for use with the types of gas
indicated on the rating plate. A conversion kit issupplied with the appliance.

ATTENTION : CES INSTRUCTIONS DOIVENTDEMUERER AVEC LE PROPRIÉTERE D’UNE
MAISON.
AVERTISSEMENT: Assurez-vous de bien
suivreles instructions données dans cettenotice pour réduire auninimum le risqued’incendie ou d’explosion ou pour éviter
tout dommage matériel, toute blessure ou la
mort.
– Ne pas entreposer ni utiliser d’essence ni
d’autres vapeurs ou liquides inflammables
dans le voisinage de cet appareil ou de tout
autre appareil.
– QUE FAIRE SI VOUS SENTEZ UNE ODEUR DE GAZ:
• Ne pas tenter d’allumer l’appareil.

• Ne touchez à aucum interrupteur.
Ne pas vous servir des téléphones setrouvant dans le bâtiment où vous
trouvez.

• Appelez immédiatement votre
fournisseur de gaz depuis un voisin.
Suivez les instructions du fournisseur.

• Si vou ne pouvez rejoindre lefournisseur de gaz, appelez le service desincendies.

– L’installatione l’entretien doivent êtreassurés par un installateur ou un service
d’entretien qualifié ou par le fournisseurde gaz.

INSTALLER: Leave this manual with the appliance.

CONSUMER: Retain this manual for future reference.

1137945_Rev_F 7.29.10




THIS OWNER’S MANUAL PROVIDES INFORMATION TO
ENSURE SAFE INSTALLATION AND EFFICIENT, DEPENDABLEOPERATION OF YOUR FIREPLACE INSERT. PLEASE READ
THESE INSTRUCTIONS IN THEIR ENTIRETY AND MAKE THEMAVAILABLE TO ANYONE USING OR SERVICING THIS GAS INSERT.
DO NOT ATTEMPT TO ALTER OR MODIFY THE CONSTRUCTION
OF THIS APPLIANCE OR ITS COMPONENTS. ANY
MODIFICATION OR ALTERATION WILL VOID THE WARRANTY,CERTIFICATION AND LISTING OF THIS APPLIANCE.

Your stove has a unique serial number stamped on therating plate which is hung on the back. Please record
the serial number in the space below. You may also wish
to attach your purchase receipt to this page for futurereference.
MODEL NAME: Jøtul GF 300 BV Gas StoveSERIAL NUMBER:_______________________________DATE OF PURCHASE:____________________________AUTHORIZED DEALER:__________________________ADDRESS ___________________________________
PHONE: ____________________________________THIS PRODUCT MUST BE INSTALLED BY
A LICENSED MASTER OR JOURNEYMANPLUMBER OR GAS-FITTER WHEN
INSTALLED IN THE COMMONWEALTH OFMASSACHUSETTS.

Suggested Tools for
Installation and Service• External regulator (for Propane only)• Piping which complies with local code
• Manual shut-off valve T-Handle required in Massachusetts• Sediment trap - if required by code
• Tee joint• Pipe wrench• Pipe sealant• 10 mm open end wrench• 1/2”, 7/16” open end wrench• Phillips head screwdriver• Flat head screwdriver• 1/4” nut driver• Gloves• Safety glasses• Torx T-20 screwdriverWe� recommend thatour gas products beinstalled and serviced byprofessionals who are
certified in the U.S. by
the National Fireplace
Institute® (NFI) as NFI Gas
Specialists.

INSTALLER:__________________________________
FUEL TYPE:____________________________________
FUEL CONVERSION:

NO _______

YES_____NOTES:__________________________________________________________________________________________________________________________________________________________________________________

2

67.5%
Jøtul GF 300 BV

Table of Contents
Service Tools . ............................................ 2
Specifications.............................................4
General Information................................. 5
Safety Information . .................................6
Installation Requirements
Location . ...............................................6
Hearth Protection . ..............................6
Clearances.............................................. 7
Mantel & Trim....................................... 7
Alcove ..................................................... 7
Vent Requirements.................................10
Fuel Conversion......................................... 11
Gas Connection.........................................13
Gas Pressure............................................. 14
Log Set Installation..................................15
Flame Adjustment ................................. 16
Wall Thermostat...................................... 16
Remote Control........................................ 16
Decorative Pipe ........................................17
System Check............................................17
Operation.................................................. 18
Maintenance............................................ 19
Glass Replacement.............................. 19137945_Rev_F 7.29.10

Jøtul GF 300 BV Allagash
Natural Vent Gas Stove
Manufactured and Distributed by:
Jøtul North America
55 Hutcherson Dr.
Gorham, Maine 04038

Accepted For Use
City of New York
Department of Buildings
MEA No. 369-04-E

Test Standards

This appliance complies with National Safety
standards and is tested and listed by Intertek
Testing Services of Middleton, Wisconsin to ANSI
Z21.88-2005, ANSI Z21.88a/CSA 2.33a-2007,
CAN/CGA 2.17-M91 and CSA P.4. 01.2 for Canada.

DO NOT ATTEMPT TO ALTER OR MODIFYTHE CONSTRUCTION OF THE APPLIANCE
OR ITS COMPONENTS. ANY MODIFICATIONOR ALTERATION WILL VOID THE WARRANTY,CERTIFICATION AND LISTING OF THIS APPLIANCE.

Optional Blower . .................................. 20
Optional Antique Brick Kit ...................22
High Altitude Adjustment....................23
Mobile Home Installation ....................23

Illustrated Parts Breakdown.................24
Replacement Parts List...........................25
Warranty Statement.............................. 26
Lighting Instructions............................. 273137945_Rev_F 7.29.10

GF 300 BV Allagash
Specifications
The Jøtul GF 300 BV Allagash is a atmosphericallyvented gas fireplace heater designed only for verticalventing directly to the outside of the house, using
listed, Type B-vent pipe.

Input Rates
Natural Gas

		26,000 BTU/hr. maximum input
15,000 BTU/hr. minimum input

THIS FIREPLACE IS SHIPPED FROM THE FACTORYFOR USE WITH NATURAL GAS ONLY. FOR USE
WITH PROPANE, THE APPLIANCE MUST FIRST BE
CONVERTED USING #155592 FUEL CONVERSIONKIT PROVIDED. CONVERSION SHOULD BE MADE
BEFORE THE APPLIANCE IS INSTALLED. SEE PG. 11.

Propane26,000 BTU/hr. maximum input
13,500 BTU/hr. minimum input

Inlet Pressure:

MIN. 		MAX.

Natural Gas:
Propane:5.0 WC (1.24 kPa)
7.0 WC (1.74 kPa)
12.0 WC (2.99 kPa) 14.9 WC (3.71 kPa)

Natural Gas:
Propane:1.2 WC (.30 kPa)
2.9 WC (.722 kPa)

Manifold Pressure:

MIN. 		MAX.

3.8 WC (.95 kPa)
11.0 WC (2.74 kPa)

Piezo Ignitor / Standing Pilot
CL

11 1/2”292 mm4 1/2”
114 mmCL
16 1/2”420 mm

23”
584 mmWith Short Legs, reduce height by 2 1/4” ( 51 mm)

CL

27 3/4”705 mmRear Exit
21 5/8 ”
550 mm22 1/4”565 mm

4

13”
330 mmTop
ExitFlue
Collar25”
635 mmTop Plate
27 3/4”705 mmGeneral Information

 THIS HEATER MUST BE INSTALLED AND MAINTAINEDBY A QUALIFIED SERVICE AGENCY.

 The installation and repair of this appliance must be

done by a qualified service person. Failure to properly
install and maintain this heater could result in an
unsafe or hazardous installation, which may result ina fire, explosion, property damage, personal injury or
loss of life.

 This appliance may be installed in an aftermarket

permanently located, manufactured (mobile) home,where not prohibited by local codes.

This appliance is only for use with the type(s) of gas
indicated on the rating plate. This appliance is notconvertible for use with other gases, unless a certified
kit is used.

Cet appareil peut être installé dans un maison préfabriquée (mobile) déjà installée à demeure si les règlements locaux le permettent.
Cet appareil doit être utilisé uniquement avec les
types de gas indiqués sur la plaque signalétique. Ne
pas l’utiliser ave d’autres gas sauf si un kitde conversion certifié est installé.

 This appliance should be inspected before use andat least annually. More frequent cleaning may berequired due to excessive lint from carpeting, bedding
material, etc. It is imperative that control compartments, burners, and circulating air passageways of
the appliance be kept clean.

 THIS APPLIANCE MUST NOT BE CONNECTED TO A

CHIMNEY OR FLUE SERVING ANY OTHER APPLIANCE.

 The installation must conform to local codes. Your lo-

137945_Rev_F 7.29.10

Consult the local or national installation code(s) toassure that adequate combustion and ventilation air isavailable.

 Installer l’appareil selon les codes ou reglements

locaux, ou, en l’absence de tels reglements, selon les
Codes d’installation CAN/CGA-B149.

 DO NOT OPERATE THIS STOVE IF ANY PART HAS BEEN

UNDER WATER. Call a qualified service technician toinspect the heater and to replace any part of the control system and any gas control which may have been
under water.

 Ne pas se servir de cet appareil s’il a ete’ plonge dansl’eau, completement ou en partie. Appeler un technicien qualifie pour inspecter l’appareil et remplacer
toute partie du syste’me de controle et toute commande qui ont ete plonges dans l’eau.

Glass Panel

Do not operate this appliance with the glass
front removed, cracked, or broken. Replacementof the glass should be done by a licensed or
qualified service person. Only remove glass forroutine service. Always handle glass carefully.

Unpacking your stove
1. Remove the Top Plate of the stove by simply lifting it
straight off of the stove body.

2. To open the firebox, disengage the two Glass Frame
Latches located on top of the firebox. Pull each handle
forward to clear the latch from the notch in the frame.

3. Familiarize yourself with the installation requirements

cal Jøtul dealer can assist you in determining what isrequired in your area for a safe and legal installation.
Some areas require a permit to install a gas burning
appliance. Always consult your local building inspector, or authority having jurisdiction, to determine
what regulations apply in your area.

Glass Frame
Latch

 CODE COMPLIANCE: Your local officials have final

authority in determining if a proposed installation is
acceptable. Any requirement that is requested by the
local authority having jurisdiction, that is not specifically addressed in this manual, defaults to local code.
In the absence of local codes, the installation requirements must comply with the current edition of
National codes. In the U.S., these requirements are established in the National Fuel Code, ANSI Z223.1.(NFPA
54) current edition. In Canada, the codes have been
established in CAN/CGA B149 Fuel Installation Code,current edition.

specified in this manual, before beginning the installation.

Hardware Bag Contents• Fuel Conversion Kit - LP ...................................155592* Decorative Pipe Brackets ................................129469

5

137945_Rev_F 7.29.10

Safety Information

Location

 Children and adults should be alerted to thehazards of high surface temperatures and should
stay away to avoid burns or clothing ignition.

The GF 300 BV may be located on or near conventional construction materials, however, proper clearance
to combustibles must be maintained in order to provide
adequate air circulation around the appliance. Also, it isimportant to provide adequate access around the stove
for servicing and proper operation.

 Due to the high operating temperatures thisappliance should be located out of traffic andaway from furniture, draperies, etc. Maintainproper clearance to combustible mantels andfireplace trim.

 Young children should be supervised while they
are in the same room as the appliance. Toddlers,
young children and others may be susceptible
to accidental contact burns. A physical barrier,such as a child guard, is recommended to be used
if there are at-risk individuals in the house. To
restrict access to a fireplace or stove, install an
adjustable safety gate to keep toddlers, young
children and other at-risk individuals out of theroom and away from hot surfaces.
 Any safety screen or guard removed for servicing
an appliance must be replaced prior to operating
the appliance.

 Clothing or other flammable materials should not
be placed on or near the fireplace.
 Surveiller les enfants. Garder les vêtements, lesmeubles, l’essence ou autres liquides à vapeur
inflammables lin de l’appareil.

 Never allow anyone to use the fireplace if they are
unfamiliar with its operation.
 NEVER store or use gasoline or any otherflammable vapors or liquids in the vicinity of thefireplace.

 Never burn any solid materials (wood, cardboard,paper, coal, etc.) in this gas fireplace. Use withnatural gas or propane fuel ONLY.

In selecting a location for the stove, consider thefollowing points:
1) Heat distribution2) Vent termination requirements
3) Gas supply line routing
4) Traffic areas, furniture, draperies, etc.

The clearance and hearth specifications listed in thismanual are the minimum requirements for combustible
material. A combustible material is anything that canburn (i.e. sheet rock, wall paper, wood, fabrics etc.). Thesesurfaces are not limited to those that are visible and also
include materials that may be located behind non-combustibles.

If you are not sure of the combustible nature of amaterial, consult your local fire officials. “Fire Resistant”
materials are considered combustible: they are difficult toignite, but will burn. Also, “fire-rated” sheet rock is considered combustible.

Hearth Requirements

The GF 300 BV gas stove CANNOT be installed directly on
carpeting, vinyl, linoleum or Pergo®.
If this appliance will be installed on any combustible
material other than wood, a floor pad must be installedthat is either metal or wood, or a listed hearth pad. Thisfloor protection must extend the full width and depth of
the appliance. It is not necessary to remove carpeting,vinyl or linoleum from underneath the floor protection.
See fig. 1.
Figure 1. Minimum Hearth Protection.

 Any safety screen, glass or guard removed forservicing the appliance must be replaced prior tooperating the appliance.

14”(356 mm)

 Do not slam or strike the glass panel.

 This appliance is NOT for use with aftermarket
glass doors.
Cet appareil ne sert pas avec des portes en verrede marché des accessoires.
 Wear gloves and safety glasses while installingor performing maintenance procedures on thisappliance.

624”(686 mm)

137945_Rev_F 7.29.10

Stove and Vent Clearance
Requirements
Minimum Clearances from the Stoveto Combustibles See figs. 2-3.
Rear:
Ceiling:Corner:Sides:

2”(51 mm)To Rear Wall2” (51 mm) - measured from Draft Hood
32 1/4” (819 mm) - measured from stove top
3” (76 mm) - measured from stove top
3” (76 mm) - measured from stove top

Minimum Clearances from the Vent Pipe to
Combustibles

Horizontal Run:
Top: Off the top of the pipe2” (50 mm)
Sides: Off the sides and bottom 2” (50 mm)

3”(76 mm)

3”(76 mm)Figure 2. Parallel Installation Clearances.

Vertical Run:All sides: 1” (25 mm)


All vent components must be installed in accordance withthe manufacturer’s instructions and within the terms of
their listing. Refer to the manufacturer’s instructions forapproved clearances from the vent pipe to combustible
materials.

 



36” (914 mm)
24” (610 mm)
61” (1550 mm)

Mantel Clearances -

Maintain clearances to combustibles as noted above.

Width:
Depth:Height:




Minimum Alcove Dimensions

 

Figure 3. Vent adaptor centerline at minimum clearance
to corner walls.

Stove shown with standard legs. With Short Legs, subtract 2 1/4” (51 mm)from the clearances indicated below.








  





     

 



 
  
  
     
   
 







 



  

Figure 4. Mantel and Trim specifications Stove installed flush with fireplace face.




Figure 4a. Mantel specifications Stove recessed into fireplace no more than 6 1/2”.

7

137945_Rev_F 7.29.10

Vent Requirements
The GF 300 BV Allagash is specifically designed to operateusing 4” Type B vent pipe components or a Listed Flexible
gas liner.
• All venting components must be installed in accordance with the terms of their listing and manufacturer’s instructions.

• The minimum height of a vertically terminated systemshall be no less than 7’, and the maximum height shallbe no more than 35’. See diagrams page 9.
• With steep roofs, nearby trees, and in predominant
windy conditions, poor draft or down draft conditions
can occur. In these cases, increasing the height of thevent or high wind termination caps may improve thesituation.

• ELBOWS: If an offset or elbow is necessary in the vertical rise, it is important to support the vent pipe every
three feet, to avoid excessive stress on the offsets.
• Whenever possible use 45° elbows opposed to 90°
elbows. This offers less restrictions for the flow of fluegases.

H=

Min.
HeightRoof Pitch

in Ft.

Flat to 6/12......................... 1.0
Over 6/12 to 7/12.............. 1.25
Over 7/12 to 8/12............... 1.5
Over 8/12 to 9/12.............. 2.0
Over 9/12 to 10/12............ 2.5
Over 10/12 to 11/12............ 3.25
Over 11/12 to 12/12............ 4.0
Over 12/12 to 13/12............ 5.0  
  Over 14/12 to 16/12........... 6.0
Over 16/12 to 18/12........... 7.0
Over 18/12 to 20/12.......... 7.5
      

   


         
 
 ­ Maximum number of 90° elbows: three
Maximum number of 45° elbows: four

• TOTAL MAXIMUM HORIZONTAL RUN ANYWHERE IN
THE VENTING CONFIGURATION IS 4 FEET. The distance
between any 45° elbows is considered a horizontal run.
See diagrams, page 10.
• Any Type B vent passing through a roof must havea flashing, storm collar, thimble and a Type B cap isrequired. See diagrams, page 10.

• Venting on the Allagash CANNOT be less than 4” indiameter or greater than 4” in diameter.

• Any unused flue or masonry enclosure can be used as apassage way for venting, but the flue must be relined
using Type B 4” vent or Listed Flexible Gas Liner.
• The remaining space around the liner in a masonry or
zero-clearance flue CANNOT be used to vent any otherappliance.
• When terminating through the roof refer to the Gas
Vent Rule for proper vent termination height.
See fig. 5.
• NO venting may terminate horizontally or below

8

Figure 5. Termination Height Requirements.
roof eaves.

• Passage through combustibles (walls, ceilings) must
be with Type B venting and must maintain listed
clearances.
• Any horizontal run should have an upward slope of
1/4” per foot toward the termination cap.

• When venting through a thimble into a masonry
flue, any venting exposed in the room must be TypeB venting, or a flexible liner sleeve within 24 ga. 6”
stove pipe.

• Listed Flexible Gas Liners may not be exposed in any
living space.

137945_Rev_F 7.29.10• When 6” diameter decorative pipe is installed tocover the venting any Listed Flexible Gas liner must
be connected directly to the stove’s draft hood.

• Use of single wall connector pipe as a vent is prohibited for use with the GF300 Allagash B-Vent stove.
• A firestop is required at every floor.

• Any venting that is exposed above the first floor,
regardless of attic space or living space, must be
enclosed. Always maintain the required clearance
from all sides of the vertical vent system according
to manufacture.

• Installation of any components not manufactured orapproved by Jøtul or failure to meet all clearance requirements will void all warranties and could resultin property damage, bodily injury, or serious fire.
• Never modify any venting component, or use any
damaged venting product.

• THE GAS APPLIANCE AND VENT SYSTEM MUST BE
VENTED DIRECTLY TO THE OUTSIDE OF THE BUILDING, AND NEVER ATTACHED TO A CHIMNEY SERVINGA SOLID FUEL OR GAS BURNING APPLIANCES.

Venting through a Masonry or
Prefabricated Manufactured
Chimney
Top sealing
achor plate

NOTE:

Listed termination cap
required

Type B vent or
Listed Flexible Gas
Liner.
Use of Type B
vent liner within
outside chimneys
is recommended tohelp keep the gases
warm and stabilize
draft.
Max. Height 35 ft.
Min. Height 7 ft.
Alwaysmaintain
the proper
clearance tomantel andtrim• BE SURE TO MAINTAIN THE PROPER CLEARANCES TOCOMBUSTIBLES AS DEFINED IN THIS MANUAL AND
IN THE INSTRUCTIONS PROVIDED WITH EACH VENTING COMPONENT.

• When installing at an altitude above 2000’ the minimum vertical rise becomes 12’ from the draft hood.

Storm collar
required

Maximum
offset is 4 ft.
Recommended damper
sealing plate to seal
flue chamber to prevent heat loss

A chimney system located outside the building
envelope may be subject to downdrafting
and/or flow reversal. Atmospherically-vented appliances, such as B-Vents, may not be compatible
with these chimney systems.

All atmospherically-vented appliances (B-Vents)
are affected by atmospheric conditions and housepressurization. For example, a B-Vent appliancevented to an outside chimney system in a basement will likely be subject to negative pressure.
This type of installation is not recommended.

WARNING: FAILURE TO POSITION THE PARTS IN ACCORDANCE WITH THIS DIAGRAM OR FAILURE TO USE ONLYPARTS SPECIFICALLY APPROVED WITH THIS APPLIANCE
MAY RESULT IN PROPERTY DAMAGE OR PERSONALINJURY.

Figure 6. GF 300 BV venting through a masonry chimney.

9137945_Rev_F 7.29.10

Approved B-Vent Configurations
Listed B-Vent
Termination
Cap required.

Listed B-Vent Termination Cap required.
Maximum
chimneyheight off
Draft Hood is
35 feet.

NOTE:
Installation ataltitude greaterthan 2000’ requires minimum
12 ft. vertical risefrom Draft Hood.

NOTE:
Installation ataltitude greaterthan 2000’ requires minimum
12 ft. vertical risefrom Draft Hood.

Minimum
chimneyheight off
Draft Hood is
7 feet.

Figure 7.

Figure 8.

Maximum
chimneyheight off
Draft Hood is
35 feet.
Minimum
chimneyheight off
Draft Hood is
7 feet.

NOTE:
Installation ataltitude greaterthan 2000’ requires minimum
12 ft. vertical risefrom Draft Hood.

10

Listed B-Vent
termination
cap required.

Maximum
total horizontal
anywhere inventing configurationis 4 feet.

Minimum chimneyheight from Draft
Hood
is 7 feet.
Max. Four, 45°
or Three, 90°
ElbowsMaximum
total horizontal
anywhere inventing configurationis 4 feet.

Figure 9.

Minimum chimneyheight from Draft
Hood
is 7 feet.

Max. Four, 45°
or Three, 90°
ElbowsListed B-Vent
termination cap
required.

NOTE:
Installation ataltitude greaterthan 2000’ requires minimum
12 ft. vertical risefrom Draft Hood.

Maximum
total horizontal
anywhere inventing configurationis 4 feet.

Figure 10.

Fuel Conversion
The GF 300 BV gas stove is shipped from the factoryequipped to burn NATURAL GAS only. If PROPANE gas is
to be used as fuel, the appliance must first be converted
for use with propane. Use Propane Conversion Kit 155592,
supplied with the appliance.

Order and install NG Conversion Kit 155593 to changeback to use with natural gas.
WARNING:THE CONVERSION KIT IS TO BE INSTALLED BY AN
AUTHORIZED JØTUL SERVICE TECHNICIAN IN ACCORDANCE WITH THE MANUFACTURER’S INSTRUCTION AND ALL CODES AND REQUIREMENTS OF THE
AUTHORITY HAVING JURISDICTION. FAILURE TO
FOLLOW THESE INSTRUCTIONS COULD RESULT IN
SERIOUS INJURY OR PROPERTY DAMAGE. THE QUALIFIED AGENCY PERFORMING THIS WORK ASSUMESRESPONSIBILITY FOR THIS CONVERSION.
IN CANADA:THE CONVERSION SHALL BE CARRIED OUT IN ACCORDANCE WITH THE REQUIREMENTS OF THE PROVINCIAL AUTHORITIES HAVING JURISDICTION AND
IN ACCORDANCE WITH THE REQUIREMENTS OF THE
CAN1-B149.1 AND .2 INSTALLATION CODE.
AVERTISEMENT:CET EQUIPEMENT DE CONVERSION SERA INSTALLE PAR UNE AGENCE QUALKFIEE DE SERVICECONFORMENMENT AUX INSTRUCTIONS DU FABRICANT ET TOUTES EXIGENCES ET CODES APPLECABLES DE L’AUTORISES AVOIR LA JURIDICTION. SI
L’INFORMAITON DANS CETTE INSTRUCTION N’ESTPAS SUIVIE EXACTEMENT, UN FEU, EXPLOSIONOU PRODUCTION DE PROTOXYDE DE CARBONE
PEUT RESULTER LE DOMMAGES CAUSER DE PROPRIETE, PERTE OU BLESSURE PERSONNELLE DE VIE.
L’AGENCE QUALIFIEE’ DE SERVICE EST ESPONSABLE
DE L’INSTALLATION PROPRE DE CET EQUIPEMENT.
L’INSTALLATION N’EST PAS PROPRE ET COMPLETEJUSQU’A L’OPERATION DE L’APPAREIL CONVERTI ESTCHEQUE SUIVANT LES CRITERES ETABLIS DANS LESINSTRUCTIONS DE PROPRIETAIRE PROVISIONNEESAVEC L’EQUIPEMENT.

Conversion Kit Contents:

137945_Rev_F 7.29.10• 1, regulator tower labeled for propane• 3, regulator tower screws• 1, burner orifice (#39 for NG, #53 for LPG)
• 1, pilot orifice (#51 for NG, #30 for LPG)

• Label A - to be completed and applied to 			the back of the stove• Label B - apply to the stove’s Rating Plate• Small valve label - apply to valve body

Conversion instructions are also shipped in the stove with theconversion kit.

Fuel Conversion Procedure
1. Turn off gas supply to stove.
2. Remove the stove Top Plate.

3. Disengage the two Glass Frame Latches at the top of
the firebox. See illustration on page 5. Carefully lift theglass panel up and out of the stove.
4. If installed, remove the Embers and Log Set using care
not to damage the fragile log parts.
5. Lift out the Burner Skirt shown in fig.11.

6. Reach under the stove and remove the Air Shutter
wingnut from its stud. As you face the right side, it is
the one closest to you. See fig. 12.

Burner Skirt

Figure 11. Lift and remove the Burner Skirt from within
the firebox.

Tools required:• 1/2” open ended wrench or deep-well socket, Torx T20
or slotted screwdriver, 4 mm allen wrench.



Figure 12. Locate and remove the Air Shutter wingnut
from under the right side of the stove.

11

137945_Rev_F 7.29.10

7.

8.

Lift out the Burner Plate: NOTE: There are no screws
securing the Burner to the floor of the firebox. Pull
the Air Shutter forward and lift the burner together
with shutter up and out of the stove as a unit. See fig.
13.
Change the Burner Orifice. See fig. 14. Using a ½”
open ended wrench or deep-well socket remove theburner orifice from its brass elbow housing and replace with the appropriate orifice supplied in the kit.

9. Replace the Air Shutter with its gasket and push it
all the way back to allow replacement of the Burner
Plate. Reattach the wingnut to the shutter stem under the stove, but do not tighten. You will set its final
position later.

10. Replace the Burner Plate. Engage the burner tube
with the Air Shutter assembly as in fig. 13. Be surethe burner is securely engaged with the two support
brackets at the front of the firebox and push the plateback toward the rear of the firebox. When correctly
positioned, there will be 1/2” (13 mm) clearance between the burner plate and the front of the firebox.
See fig. 15.

Air Shutter

Burner Plate

Figure 13. Remove the Air Shutter and Burner as a unit.

Burner Orifice

11 . CHANGE THE PILOT ORIFICE: From within the firebox,
remove the Pilot Head by pulling it straight up fromthe pilot base. See fig. 16. Using the 4 mm hex key
included with the kit, unscrew the pilot orifice (counterclockwise). Replace with the appropriate orifice:

12. Tighten orifice into the base of the pilot assembly. To
prevent bypass leaks, be sure the orifice is secured
tightly and flush with the base. Replace pilot head bypushing it down onto the pilot base.

Figure 14. Change the Burner Orifice.

13. Replace the Variable Regulator. Using a Torx T-20
screwdriver, remove the three screws from the frontof the valve regulator. See fig. 17.
14. Remove the Regulator Tower, Gasket, white plastic
disk, and Spring. Remove the black rubber gasket
from the valve. See fig. 17.

1/2”

Figure 15. Correct Burner Position - maintain 1/2 inchclearance between burner and firebox front.

12137945_Rev_F 7.29.10

Pilot Head

Ignitor
Thermocouple

Orifice

Regulator Tower
Thermopile
Remove black gasket
from regulator assembly
Retainer
Clip

Valve
Pilot Base
Figure 16. Pilot orifice removal and replacement.
15. Install the new regulator: Be sure the new gasket isproperly positioned and tighten screws securely.
16.

Install the identification labels to the stove sothat they can be seen by any person that may be servicing the stove.
Label A: apply to back of stove.
Label B: apply to stove’s rating plate.
Small valve Label: apply to valve.

17. Reassemble the stove, apply gas to the system andcheck for leaks using a soapy water solution.

NEVER USE AN OPEN FLAME TO CHECK FOR GAS LEAKS.

18. Correct gas pressure is essential for efficient and safe
operation of this appliance. Use a manometer to checkpressures as specified in the Gas Pressure section ofthis manual (page 15).

19. Adjust the Air Shutter. You will need to position the
shutter to provide a gas/air mixture that will achieve
the best flame picture with your particular installation.
Start with the shutter stem at the half-way position in
the slot in the bottom of the stove. See fig. 12. Pushing
the stem back will restrict air, while pushing it forward will open the shutter and increase air. With someexperimentation, you will find the shutter position thatworks best for your installation.
ALWAYS REFER TO THE LIGHTING INSTRUCTIONS ON THE
INSIDE BACK COVER OF THIS MANUAL WHEN LIGHTINGYOUR STOVE.

Figure 17 Regulator assembly.

Gas Supply Connection
BLOWER NOTE: Install the optional blower before
connecting the gas line in order to ensure adequate
clearance between both.
The gas supply line connection is made to the left side of
the front-mounted valve. The gas supply line should be3/8” npt with a 1/2” diameter supply, or the appropriate
size to provide sufficient gas pressure to the valve regardless of the input setting.
The use of Flexible Gas Appliance Connectors is acceptable in many areas in the U.S. However, Canadian
methods vary depending on local code.

ALL INSTALLATIONS MUST COMPLY WITH LOCAL CODEOR IN THE ABSENCE OF LOCAL CODE, MUST COMPLY WITH
THE MOST RECENT EDITION OF THE NATIONAL FUEL GASCODE ANSI Z223.1/NFPA 54 OR CAN-B149.
All codes require a gas shut-off valve (gas cock) andunion, to be installed in the supply line, and in the sameroom as the appliance. This allows for the disconnectionof the stove for servicing and maintenance. See fig. 18.
A T-HANDLE GAS COCK IS REQUIRED IN
MASSACHUSETTS TO COMPLY WITH CODE 248CMR.

Secure all joints tightly using appropriate tools andsealing compounds. For propane units be sure to use compounds that are propane resistant. Turn on gas supply andtest for gas leaks using a soapy water solution. Never use
an open flame to check for leaks.

13

137945_Rev_F 7.29.10
 



    


E

A

Figure 19. Pressure test points.
 

 



 

Figure 18. Supply valve connection fittings.

Leak test:

1. Mix a 50-50 solution of water and dishsoap.

2. Light appliance- see lighting instructions
on the inside back cover of this manual oron the stove’s rating plate.
3. Brush or spray all joints and connections
with the soapy water solution.
4. If bubbles appear at any connection orseam or a gas odor is detected, immediately turn gas control knob to the OFF
position.
5. Tighten or reconnect the leaking joint
and retest for any gas leaks.

Gas Pressure

Correct gas pressure is essential for efficient and safe
operation of the GF 300 BV gas stove. It is importantthat the correct pressure is established at the time of
the installation. Proper gas pressure provides a consistent flow of gas to the appliance and is instrumental inchecking for gas leaks.
Pressure Test: Attach a manometer to the appropriate test point on the valve. See fig. 19. The gauge
connections are located on the front of the valve under
the On/Off/Pilot- knob. Gauge connections are identified by:

E - for Inlet or Supply Pressure (the amount of gas
coming to the valve.)
A - for Manifold Pressure (the amount of gas thatis coming out of the valve to the burner.)
ALWAYS TEST PRESSURES WITH VALVE CONTROLKNOB SET ON HIGH.

14

		

INLET GAS PRESSURES(inches water column)

NATURAL GASPROPANE

MIN
5.0
12.0

MAX
7.0
14.9

The appliance and its appliance main gas valve
must be disconnected from the gas supply piping
system during any pressure testing on that systemat test pressures in excess of 1/2 psig (3.5 kPa).

The appliance must be isolated from the gas
supply line by closing its individual manual gas
shut-off valve (gas cock) during any pressure testingof the gas supply piping system that is equal to orless than pressures of 1/2 psig (3.5 kPa).

		MANIFOLD PRESSURES(inches water column)
MIN
MAX

NATURAL GASPROPANE

1.2
2.9

3.8
11.0

137945_Rev_F 7.29.10
PN 220729

Log Set Installation

Brick Kit Note: Install the optional Antique Brick Kit
155370 before installing the logset. See page 22 and the
instructions provided with that kit.

The GF 300 BV logset must be installed before operating
the burner. The logset includes four log pieces, packaged inside the firebox, and a quantity of ember stones
packaged in the Miscellaneous Parts bag. To install thelog set, remove the packaging and place the parts inside
the firebox as illustrated in figures 20-24. Do not handle
the log set with your bare hands. Always wear gloves toprevent skin irritation from the ceramic fibers.

Figure 21. Install Right Log

PN 220728

IMPORTANTThe ember stones realistically simulate glowing coals when the burner is operating. Theseshould be spread evenly over the burner plate andaround the logs.

TO INSURE PROPER BURNER FUNCTION, DO
NOT OBSTRUCT THE PILOT ASSEMBLY AND BURNER SKIRT OPENINGS WITH EMBER STONES. KEEPEMBERS OFF OF THE PILOT CARRY-OVER PORTS. SEE
FIG. 24.

Figure 22. Install Left Log

You do not need to use all of the ember
stones. With some experimentation, you will findthe arrangement and quantity of embers thatworks best with your stove. Depending upon thecharacteristics of your installation, it is possiblethat too many ember stones can promote sooting
on the logs. Adjust the quantity of ember stones
as appropriate to maintain the best overall flame
picture and burner performance.

PN 220730

Figure 23. Install Middle Log

PN 220727

KEEP CARRY-OVER
PORTS CLEAR
Pilot
Assembly

1/4
6 mm

Figure 20. Engage the holes in the underside ot the Rear
Log with the two pegs in the burner skirt.

1/4
6 mm

Figure 24. Position embers loosely and maintain 1/4”
clearance from the burner skirt edges.

15137945_Rev_F 7.29.10

Flame Appearance / Air Shutter
Adjustment

The GF 300 BV gas stove is shipped from the factoryequipped to burn Natural gas. If the stove has been
converted for use with propane, the Air Shutter may
require adjustment to achieve the desired flame
appearance. Other installation related variables can also
affect the flame picture. The Air Shutter may be opened orclosed to provide the best flame picture for your specificinstallation.

Too large an air opening - the appliance will generate aflame that is blue and transparent, or an “anemic” flame.
Too small an air setting - the appliance will generatevery long yellow flames resulting in soot. Sooting
produces black deposits on the logs, on the inside walls of
the appliance, and potentially on the exterior termination
cap. Sooting is caused by incomplete combustion in the
flames and lack of combustion air entering the air shutter
opening.
To adjust the air shutter:

1. Reach under the right side of the stove and loosen thewingnut located closest to you. See fig. 25. Slide thewingnut stud forward to open the air shutter and backto provide less air. Make adjustments in small increments.
2. Tighten the wingnut to secure the shutter at the desired setting.

3. Allow the stove to burn for 30 minutes on the HIGH setting, observing the flame continuously. If the flame appears weak, slow, or sooty, repeat the process describedabove until the flame is as desired.

WARNING: AIR SHUTTER ADJUSTMENTS SHOULD ONLY
BE PERFORMED BY A QUALIFIED PROFESSIONALSERVICE TECHNICIAN.

Optional Wall Thermostat or
Remote Control

Use only a 750 millivolt DC two-wire circuit thermostat
with this appliance. The thermostat should be placedin the same room as the heater, typically 5 feet off thefloor. Avoid drafty areas or any area that may affect theaccuracy of the thermostat.

The thermostat should be connected to the GF 300
BV using a minimum of 16 gauge wire with a maximum
length of 25 feet of wire.
Connect the two thermostat wire leads to the twolower terminals on the terminal block located directly
above the ignitor button. Do not overtighten the connections. IT IS NOT NECESSARY TO DISCONNECT ANYOTHER WIRES. See Fig. 26.

For thermostatic operation, the On/Off/T-Stat switch
on the back of the stove must be in the T-stat position,and the pilot light must be running, as it is the powersource for the thermostat.
At the thermostat, the two wires should be connected to the two connection screws on the thermostat baseplate per the manufacturer’s instructions.

Remote Control

When using a remote, the remote receiver should be
wired to the terminal block the same way the thermostat would be. See the instructions above.

Follow the operating instructions included with the
Remote Control unit.
CAUTION:LABEL ALL WIRES PRIOR TO DISCONNECTION WHEN SERVICING
THE CONTROLS. WIRING ERRORS CAN CAUSE IMPROPER ORDANGEROUS OPERATION. ALWAYS VERIFY PROPER OPERATIONAFTER SERVICING THE APPLIANCE.




Black

Black




Red
White

ON
Purple

TH



OFF

TP



TSTAT

TH
TP


OrangeWhite
Yellow







Figure 25. Loosen the wingnut to adjust the air shutter.

16

Figure 26. Valve and Accessory wiring diagram.

137945_Rev_F 7.29.10

System Check

Installing Decorative Pipe

The use of decorative pipe is optional. No decorative
pipe is included with the Jøtul GF 300 BV Allagash,
however, four locator brackets are included with thestove in the hardware bag. The brackets are used tocenter the decorative pipe over the draft hood onwhich the pipe rests. Follow the procedure below to
attach the brackets to the stove.
1. Remove the four 1/4” hex head screws that attach
the 4” Flue Collar to the draft hood, but do notremove the Flue Collar. See Figure 27.

2. Align the “L”- shaped pipe brackets with the holeson the Flue Collar and attach using the four 1/4”
hex head screws, located in the Misc. Hardware
Bag.
Reminder: Do not use single wall stove pipe as thevent pipe on this appliance.

Draft Hood
Spill
SwitchSee Air Shutter/Flame Appearance section of thismanual for proper air shutter settings and adjustments. Note: the more offsets there are in the ventsystem, the greater the need for an air shutter adjustment. See page 16.

Figure 27. Decorative pipe attachment.

Figure 28. Proper pilot flame appearance.

The pilot flame should engulf the top 3/8” of thethermopile (to generate millivolt current) and the
top 1/8” of the thermocouple. The pilot flame should
project out of the pilot hood 1” at all three ports andalign with the burner carry-over ports.

NO SMOKE OR SOOT SHOULD BE PRESENT. CHECKLOG PLACEMENT IF ANY SOOT OR SMOKE IS PRESENT.
IF SOOT OR SMOKE PERSISTS, THE AIR SHUTTER MAY
NEED TO BE ADJUSTED.

6 Decorative
Pipe Brackets





2. PILOT FLAME: See figs. 28 and 28a. You can monitor
the pilot flame through the view port located at therear under the Right Log. The pilot flame should besteady - not lifting or floating. The flame should beblue in color around the pilot hood, with traces of yellow toward the outer edges.

3. BURNER ADJUSTMENT: This stove is equipped witha variable gas control valve that allows easy adjustment of the flame height appearance and heat
output. To adjust the flame between the HI and LOW
setting, rotate the HI/LOW knob, located in the centerof the valve face. Fire intensity can be adjusted up to
50% between the LOW and HIGH settings. See fig.
29.

Flue Collar

1. PURGING THE GAS LINE: When lighting the appliancefor the first time, it will take a few moments to clear
the gas line of air. Once this purge is complete, theappliance will operate as described in the lighting
instructions. See the inside back cover of this manualor the stove Rating Plate attached the bottom of thestove. Subsequent burner starts will not require purging the gas line unless the supply line is shut off.





Figure 28a. Proper pilot flame / carry-over port alignment.

17

137945_Rev_F 7.29.10

		
WARNING:AIR SHUTTER ADJUSTMENTS SHOULD ONLY BE
PERFORMED BY A QUALIFIED PROFESSIONALSERVICE TECHNICIAN.

If a vacuum is used during any service on the stove,
ALWAYS be sure the stove is cold and there are NO hot
embers.

5. This appliance has a continuous burning pilot flame.
Exercise caution when using products having combustible vapors. Always shut-off gas supply while servicing
the stove.

6. CAUTION: DO NOT OPERATE THIS APPLIANCE WITH THE
GLASS REMOVED CRACKED OR BROKEN.
Replacement of the glass should be done by a licensed
or qualified service person. Use only replacement glass
provided by your authorized Jøtul dealer. Never use
any substitute materials.

Figure 29. Flame appearance on the “high” setting after
approximately 15 to 20 minutes burning.
CAUTION:
DO NOT ATTEMPT TO ALTER THE FLAME APPEARANCEBY POSITIONING THE GAS VALVE CONTROL IN ANYOTHER POSITION OTHER THAN THE FULL “ON”
POSITION.

Operation

Familiarize yourself with the controls of the GF 300 BV.
Make sure that anyone else using the appliance is alsofamiliar with the controls and operation procedures.
Always follow the Lighting Instructions on the inside backcover of this manual and also located on the Rating Plateattached to the burner assembly.
1. Once the pilot is lit, burner operation is controlled by
the rocker switch located at the left corner of the rearshroud. See fig. 30.
ON / OFF - use for manual control of the burner.
T-STAT - use for optional thermostatic or remote control operation. The burner will be controlled by thoseaccessories.

2. During the first few fires, you may notice odor and/or smoke from the stove. This is normal and resultsfrom burn-off of manufacturing residue and curing ofmaterials. You may find it helpful to provide additional
ventilation and fresh air to alleviate this condition.
3. Condensation may occur on the glass upon each lighting of the appliance. This “fog” will disappear as theappliance heats up.

4. Keep the controls and the area under the appliancefree of debris, vacuum this area frequently. Always keep
the appliance area clear and free from combustible materials, gasoline and other flammable liquids.

18

WARNING: OBSERVE CAUTION WITH THE GLASS. THE
GLASS PANEL MAY SHATTER UNEXPECTEDLY IF STRUCKWITH AN OBJECT. ALWAYS HANDLE THE GLASS PANELWITH CARE. WHEN SERVICING THE STOVE ALWAYS
PULL THE GLASS ASSEMBLY STRAIGHT UP FOR REMOVAL.

7. Clean the glass only when necessary. Wipe surface
with a clean, damp soft cloth. Follow with a dry, soft
towel as desired. Take care not to scratch the glass
surface.
WARNING: DO NOT USE ABRASIVE CLEANERS ON THE
GLASS. NEVER CLEAN THE GLASS WHEN IT IS HOT.
BLOCKED FLUE SWITCHNOTE: This appliance is equipped with a Spill Switch
which will disable the burner in the event that thevent system becomes blocked. Located on the side of
the Draft Hood, at the back of the stove, the switch
has a reset button that, when pressed, will re-enableburner function. See Fig. 27.

		If the Spill Switch repeatedly shuts the burner off,
turn off the gas supply and call your dealer or service
technician. The Spill Switch will continue to shut off
the burner until the vent problem has been corrected. Not all vent problems can be corrected as B-Vent
appliances are affected by atmospheric conditions
and house pressurization.














Figure 30. Burner Switch and Optional Blower Controls

137945_Rev_F 7.29.10

MaintenanceYour Jøtul GF 300 BV Allagash and its venting systemshould be inspected before use and at least annually by aqualified service technician.
Use the form on page 26 to keep a maintenance history of your stove.

FOR REPLACEMENT, USE ONLY JØTUL CERAMIC GLASSREPLACEMENT KIT 155599. DO NOT USE ANY OTHER
TYPE OF GLASS WITH THIS APPLIANCE.

		
IMPORTANT:ALWAYS TURN OFF THE GAS SUPPLY TO THE FIREPLACEAND UNPLUG THE FORCED AIR BLOWER BEFORE ANYSERVICE WORK IS PERFORMED ON THE FIREPLACE.

Glass Panel or Gasket Removal

Annual Cleaning

3. Lift the glass frame all the way up and out of the top of
the stove. Lay this assembly on a flat surface, protecting the frame from scratches using a blanket or towel.

Vent System

The entire vent system, including the chimney, should
be inspected and cleaned every year. If the intake andexhaust venting is disassembled for any reason, it should
be reassembled and sealed according to the manufacturer’s instructions provided at the initial installation.

1. Lift the Top Plate off of the stove.

2. Release the two Glass Frame Latches. Pull each latch
handle forward forward to disengage the latch fromthe notches in the glass frame.

3. The glass panel is held in place by four compression
clips. Use a screwdriver or small pliers to pry these up
off the edge of the glass retaining walls. See fig. 31.

4. Remove the old gasket material. See fig. 32.Glass Panelor Gasket Replacement

Burner and Logset

Periodically inspect the Firebox, Valve Compartment,
Convection Airways and optional Blower to BE CERTAIN
THAT THE FLOW OF COMBUSTION AND VENTILATION AIR
IS UNOBSTRUCTED.

The firebox should be vacuumed annually to remove
any surface build up. Use a soft brush attachment andhandle the logs carefully as they are fragile. Be sure to
vacuum or wipe off the pilot assembly and burner surfaces.

Figure 31. Use small pliers to pry up the two retainer tabs.

Glass Panel or Gasket Replacement

Glass Care

Clean the glass only when necessary. Wipe the surface
with a clean, dampened, soft cloth. Follow with a dry, soft
towel. Take care not to scratch the glass surface.
WARNING:
DO NOT USE ABRASIVE CLEANERS ON THE GLASS. NEVER
CLEAN THE GLASS WHEN IT IS HOT.

1. Wrap the new gasketing material evenly around theedge of the glass, peeling back the protective strip to
expose the adhesive as you go. Press the adhesive side
down onto the glass surface. Do not stretch the gasket.
2. Place the gasketed glass within the frame and press
each of the retainer clips back into place on the retainer walls.

Gasket Inspection

It is important that the glass gasket be inspected at least
annually. Examine the ribbon gasket for signs of deterioration and make sure the gasket has a positive seal.
Replace the gasket if necessary. Refer to the replacement
parts list on page 25.
Figure 32. Wrap the gasket around the glass panel.

19137945_Rev_F 7.29.10

Optional Blower # 155620
CONNECT THE GAS SUPPLY TO THE
STOVE BEFORE INSTALLING THISBLOWER. IF NECESSARY, USE A 90°
ELBOW OFF THE GAS VALVE TO CREATEADEQUATE GAS LINE CLEARANCE.
BE SURE ALL WIRE CONNECTIONSHAVE BEEN MADE BEFORE
CONNECTING TO POWER SUPPLY.

54

1

1. Unpack and check the contents of the blower kit.
Contact your dealer if any damage is evident or parts
are missing. See fig. 33.

3

2. Attach the Snapstat Bracket to the studs located underneath the stove in the middle of the firebox floorusing the two M6 hex nuts and a 10 mm wrench. See
fig. 34.

3. Attach the Blower to the stove with the screen opening to the rear using the two M6 flange head hex
bolts as shown in fig. 35.
4. Attach either Snapstat wire connector to either
Snapstat terminal. See fig. 35.

5. Install the Snapstat by sliding it all the way into theslot in the Snapstat Bracket as shown in fig. 34.

6. Connect the female Control Switch quick-connector
to the male control switch wire harness alreadyinstalled in the stove. See fig. 35.
7. Connect power cord to the nearest outlet.

7
Contents

Tools Required• 10 mm wrench

1. Blower
2. Snapstat Wire Harness
3. Control Switch Wire Harness
4. Snapstat
5. Snapstat Bracket
6. M6 Flange Nuts, (2)7. M6 x 12 Hex Bolts, (2)Figure 33. Blower Kit Components

 THIS BLOWER MUST BE ELECTRI-CALLY GROUNDED IN ACCORDANCE WITH LOCAL CODES OR, IN
THE ABSENCE OF LOCAL CODES,WITH THE CURRENT ANSI/NFPA
70, NATIONAL ELECTRICAL CODE
OR CSA C22.1-CANADIAN ELECTRICAL CODE.

 THIS UNIT IS SUPPLIED WITH

A THREE-PRONG (GROUNDING)PLUG FOR PROTECTION AGAINSTSHOCK HAZARD AND SHOULD BE
PLUGGED DIRECTLY INTO A PROPERLY GROUNDED THREE-PRONG
RECEPTACLE. DO NOT CUT ORREMOVE THE GROUNDING PRONGFROM THE PLUG.

 ALWAYS DISCONECT THE POWER
SUPPLY WHEN PERFORMING ANYSERVICE ON THE FIREPLACE INSERT.

20

6

2

Snapstat
BracketHex Head
Flange Nuts

Figure 34. Attach Snapstat Bracket.

137945_Rev_F 7.29.10

Figure 35. Attach Blower tothe stove bottom and connect
wires to Snapstat and female
control quick connect.

Male
Quickconnector

Snapstat
Connectors

FemaleM6 x 20 mm
Hex Bolts

Blower Operation

The optional variable-speed blower will enhance heatcirculation around the firebox and out into the room. The
blower is controlled by a heat activated switch (snapstat) that will ONLY function when the control switch
is in AUTO setting. After the fire has been burning for atime, the snapstat will react to the heat and activate theblower. Fan speed may be manually adjusted with therheostat knob. If the burner turns off, the blower will beshut off automatically when the stove cools down.
If automatic blower circulation is not desired, place
the blower control switch in the MANUAL position.


G

W

BK

BK

BK

W

G


BK

BL

BK

BK



BK




GY 

BR= QuickConnector Pin

BL GY BR
AUTO OFF MANUAL

Figure 37. Blower Wiring Diagram

Manual or
Automatic
Modes

Speed
Control












CAUTION:LABEL ALL WIRES PRIOR TO DISCONNECTION WHEN SERVICING CONTROLS. WIRING ERRORS CAN CAUSE IMPROPER
AND DANGEROUS OPERATION.
VERIFY OPERATION AFTER SERVICING.
ATTENTION:
Au moment de l’entrentien des commandes, etiquietez
tous le fils avant le debranchement. es erreurs de ceblage
peuvent entra tun fonctionnement inadequat et dan-Figure 36. Blower Controls21137945_Rev_F 7.29.10

Optional Antique Brick Kit# 155648
CAUTION!
THE BRICK PANELS AND LOG PARTS ARE EXTREMELY FRAGILE. HANDLE WITH CARE.
Read these instructions before beginning the installation.

1. Remove the Top Plate. Simply lift it up off of the stove
body. It is not fastened.

Figure 39.
Disengage thecompression latches
to remove the glass
frame.

2. Remove the Glass Frame. Disengage the two compression latches located at the top of the firebox andlift the glass frame up and off of the stove. See fig. 39.
3. If installed, remove the Logset. These parts are notfastened. Simply lift them out of the firebox. You do
not have to remove the embers.
4. Install the Lower Rear Panel. Position it up against
the back wall, resting on the burner skirt. Fig. 40.

5. Install a Side Panel. Tilt the panel, bottom edge first,
into position against the side wall. The panel will
stand on its own against the wall, fitting snugly between the rear panel and the front wall of the firebox.
Fig. 41.

Figure 40. Install Lower Rear Panel

6. Install the Upper Rear Panel. Simply rest it on theother two panels. Fig. 42.
7. Install the other Side Panel.

8. Reinstall the Logset. Refer to the Owner’s Manual if
necessary. BE CERTAIN THAT NO EMBER STONES AREBLOCKING THE PILOT ASSEMBLY OPENING. Refer to fig.
36.
9. Replace the Glass Frame. Slide the frame down theslot in the front of the firebox. Be sure to push theframe into the slot in the bottom to ensure it is fully
seated. The gasket at the top of the frame should beflush with the top of the firebox.
Pull the compression latches out to engage with the
top lip of the glass frame.

Figure 41. Install Side Panel

10. Replace the Top Plate.

Upper Rear Panel
220745
Left Panel
220998Right Panel
220999Lower Rear Panel
220990Figure 38. Brick Kit Contents

22

Figure 42. Install Upper Rear Panel137945_Rev_F 7.29.10

High Altitude Adjustment

Installations burning natural gas and located at altitudes
from 2000 - 4500 ft. (610 M - 1370 M), require compensation for the thinner air (less volume of air per cubic foot).
Higher altitudes affect the atmospheric pressure and heatvalue of gaseous fuels. The lower oxygen content in the
air and the lower gas viscosity require the use of a different orifice to achieve efficient, clean combustion at theburner tube.
For high altitude installations consult the local gas
distributor or the authority having jurisdiction for proper
rating methods. If the installer must convert the unit toadjust for varying altitudes, use Jøtul High Altitude Kit,
#155810-NG.
DO NOT DERATE THE BURNER FOR PROPANE.

In the U.S: THE DERATING KIT MUST BE INSTALLED BY
AN AUTHORIZED SERVICE TECHNICIAN IN ACCORDANCEWITH THE MANUFACTURER’S INSTRUCTIONS AND ALL
CODES AND REQUIREMENTS OF THE AUTHORITY HAVING JURISDICTION. THE INFORMATION STICKER MUST
BE COMPLETED BY THE INSTALLER AND APPLIED TO THE
APPLIANCE AT THE TIME OF THE CONVERSION. THE QUALIFIED SERVICE AGENCY PERFORMING THIS WORK ASSUMESRESPONSIBILITY FOR THIS DERATING.
In Canada: This unit has been tested for installation athigh altitudes in accordance with Canadian test standard
CAN/CGA-2.17. THE DERATING SHALL BE CARRIED OUT INACCORDANCE WITH THE REQUIREMENTS OF THE PROVINCIAL AUTHORITIES HAVING JURISDICTION AND IN ACCORDANCE WITH THE REQUIREMENTS OF THE CAN1-B-149.1
AND .2 INSTALLATION CODE.

AVERTISEMENT:
Cet equipement de conversion sera installe par une
agence qualkfiee de service conformenment aux instructions du fabricant et toutes exigences et codes applecables de l’autorises avoir la juridiction. Si l’informaiton
dans cette Instruction n’est pas suivie exactement, un
feu, explosion ou production de protoxyde de carbone
peut resulter le dommages causer de propriete, perte ou
blessure personnelle de vie. L’agence qualifiee’ de service
est esponsable de l’installation propre de cet equipement. L’installation n’est pas propre et complete jusqu’al’operation de l’appareil converti est cheque suivant lescriteres etablis dans les instructions de proprietaire provisionnees avec l’equipement.

Derating Procedure

1. Follow Steps 1-10 of the Fuel Conversion procedure
outlined on pages 11 and 12.
2. Replace the original orifice with the #40 orifice in the kit.
3. Fill out the high altitude conversion label from the kit
and attach to the rating plate or gas valve.
4. Reassemble the firebox components.
5. It may be necessary to adjust the air shutter on theburner tube. See AIR SHUTTER/FLAME APPEARANCE on
page 16 for more details.

Replace with #40
orifice

Figure 43. Change the Burner Orifice.

Mobile Home Installation

The GF 300 BV can be installed for use in a mobile homein the U.S. and Canada provided:
1. The stove is secured to the floor of the mobile home.
Use Jøtul Floor Bracket Kit #750304.

2. Provision must be made to secure an electrical groundbetween the stove and the mobile home chassis.

3. The stove is installed in accordance with Title 24 CFR,
Part 3280- Manufactured Home Construction and
Safety Standard, in the U.S. In Canada, comply with CSA
Z240.4, Gas Equipped Recreational Vehicles and Mobile
Housing.
4. Always contact your local officials about installation
restrictions and requirements in your area.

THIS APPLIANCE MAY BE INSTALLED AS AN OEM INSTALLATION IN A MANUFACTURED (MOBILE) HOME AND MUST
BE INSTALLED IN ACCORDANCE WITH THE MANUFACTURER’S INSTRUCTIONS AND THE MANUFACTURED HOMECONSTRUCTION AND SAFETY STANDARD, TITLE 24 CFR,
PART 3280. THIS APPLIANCE IS ONLY FOR USE WITH THE
TYPE OF GAS THAT IS INDICATED ON THE STOVE’S RATING
PLATE. A GAS CONVERSION KIT IS PROVIDED WITH THE GF
300 DV GAS STOVE.
THIS APPLIANCE MAY BE INSTALLED IN AN AFTERMARKET PERMANENTLY LOCATED, MANUFACTURED (MOBILE)
HOME, WHERE NOT PROHIBITED BY LOCAL CODES.
CET APPAREIL PEUT ETRE INSTALLE DANS UN MAISONPREFABRIQUEE (MOBILE) DEJA INSTALLEE A DEMEURE SI
LES REGLEMENTS LOCAUX LE PERMETTENT. CET APPAREIL DOIT ETRE UTILISE UNIQUEMENT AVEC LES TYPES DEGAS INDIQUES SUR LA PLAQUE SIGNALETIQUE. NE PAS
L’UTILISER AVEC D’AUTRES GAS SAUF SI UN KITDE CONVERSION CERTIFIE EST INSTALLE.

23

24



























  












NOTE:
Models beginning at Serial No.
30000 are configured with a frontmounted gas control valve.







Figure 44.









































   

















ONLY USE REPLACEMENT PARTSPROVIDED BY AN AUTHORIZED JØTUL
DEALER.










































































GF 300 BV Allagash
Illustrated Parts Breakdown

137945_Rev_F 7.29.10

137945_Rev_F 7.29.10

GF 300 BV Allagash Parts List				Blue Black
Ivory
Jøtul Iron
Cast Iron Parts
Matte Black
Jøtul Iron
EnamelEnamelEnamel							

1.
2.
3.
4.
5.
6.
7.

8.
9.
10.
11.
12.
13.
14.
15.
16.
17.
18.
19.
20.
21.
22.
23.
24.
25.
26.
27.
28.
29.
30.
31.
32.
33.
34.
35.
36.
37.
38.
39.
40.
41.
42.
43.
44.
45.
46.
47.
48.
49.
50.
51.
52.
53.
54.
55.
56.
57.
58.

Side Plate
Base PlateLegs, (4)Front Panel
Right DoorTop Plate
Left Door

10203292
10390092
10192592
10390192
10390492
10390292
10390392

10203285
10390085
10192585
10390185
10390485
10390285
10390385

10203310390027
10196610390127
10390427
10390227
10390327

Side Clip ....................................................................... 128401
Bolt, M6 x 12 mm (Side to Base)............................ 117130 		
Bolt, M6 x 25 mm (Side to Front)........................... 128401
Rating Plate ................................................................ 220912
Lanyard, Rating Plate . .............................................. 129159
Rivet, 1/8”..................................................................... 117946
Spill Switch ................................................................. 220916
Screw, 7 x 1/2” phillips (2)....................................... 118015		
Switch Box.................................................................... 220765
Screw, #8 x 1/2” slotted hex.................................... 117917
Rocker Switch, (2)....................................................... 220703
Rheostat, 26” leads.................................................... 220970
Rheostat Nut............................................................... 220717
Rheostat Knob............................................................ 220709
Bolt, M6 x 20 (Front to Base)................................... 117117
Nut, M6 Flange........................................................... 117968
Bolt, M6 x 20 mm (Leg to Base, 4)......................... 117117
Washer, M6 Fender.................................................... 120004
Ignitor . .......................................................................3902573
Screw, M4 x 8 phillips .............................................. 117920
Ignitor Bracket..........................................................3902576
Gas Valve, NG - 50% TD............................................ 222263
Nut, M6 Flange........................................................... 117968
Screw, 10-32 x 3/8 phillips (4)................................ 117911		
Valve Bracket (2)......................................................... 220721
Screw, M4 x 12 phillips (2)...................................... 117921		
Terminal Block, 3 Pole............................................... 118028
Terminal Block Bracket............................................. 220983
Nut, M4......................................................................... 117922
Screw, 10-32 x 3/8” phillips (2).............................. 117911
Brass Elbow, 90° 3/8” NTP........................................ 129129
Compression Sleeve (2)............................................ 129463
Compression Nut (2)................................................. 129464
Main Gas Flex Tube, 5/16” ...................................... 129462
Jam Nut......................................................................... 129152
Orifice Holder.............................................................. 220643
Burner Orifice , NG -#39 . ....................................... 129367
Burner Orifice, LP - #53............................................. 220731
Wing Nut, M6.............................................................. 117975
Washer, 2 1/4” O.D..................................................... 118023
Gasket, 2 1/4” O.D. .................................................... 220734
Air Shutter.................................................................... 220791
Bolt, M6 x 20 (Tube Holder to Burner) ................ 117117
Tube Holder, Cast Iron . ............................................ 103992
Venturi Tube .............................................................. 220631
Burner Base, Cast Iron............................................... 103991
Burner Gasket ............................................................ 220633
Burner Asby, Complete ............................................ 155336
Burner Plate, Stainless Steel .................................. 220545
Burner Skirt.................................................................. 220766
Pilot Gasket.................................................................. 129670
Pilot Spacer ................................................................. 220546
Pilot Assembly, NG..................................................... 129471
Thermopile ...............................................................3094527
Thermocouple . .......................................................... 129766
Ignitor . .......................................................................3902573

10203229
10390029
10225110390129
10390429
10390229
10390329
59.
60.
61.
62.
63.
64.
65.
66.
67.
68.
69.
70.
71.
72.
73.
74.
75.
76.
77.
78.
79.
80.
81.
82.
83.
84.
85.
86.
87.
88.
89.
90.
91.
92.
93.
94.
95.
96.

10203246
10390046
10192546
10390146
10390446
10390246
10390346

Brown
Majolica
Enamel10203247
10390047
10192547
10390147
10390447
10390247
10390347Blue
Majolica
Enamel10203248
10390048
10192548
10390148
10390448
10390248
10390348

Screw, #8 x 3/4” sheet metal (2)........................... 117986
Glass, Ceramic............................................................. 220576
Bolt, M6 x 10 mm, Flange............................................. 9962
Door Clip....................................................................... 122009
Door Hinge Pin (4)..................................................... 125960
Glass Frame............................................................ 22076292
Glass Gasket, Tadpole............................................... 129124
Replacement Glass Kit . ........................................... 155599
Firebox, Heat Exchanger ......................................... 221192
Screw, #8 x 1/2” Blk .................................................. 117917
Nut, M6 Flange (2)..................................................... 117968
Exhaust Baffle............................................................ 220763
Lower Draft Hood ..................................................... 220914
Screw, #8 x 1/2” Blk (4)............................................ 117917
Upper Draft Hood ..................................................... 220915
Draft Hood Cover Plate . .......................................... 129183
Starter Collar............................................................... 129189
Screw, #8 1/2” Blk (4)................................................ 117917
Glass Frame Latch ..................................................... 129135
Screw, #8 1/2” Blk (4)................................................ 117917
Heat Fins, (2)............................................................... 155653
Nut, M6 Flange (2)..................................................... 117968
Controls Heat Shield, (2) ......................................... 220918
Rear Shroud ................................................................ 220764
Right Log . .................................................................... 220729
Middle Log .................................................................. 220730
Rear Log ....................................................................... 220727
Left Log . ....................................................................... 220728
Screw, #8 x 1/2” Blk (4)............................................ 117917
Control Door................................................................ 221187
Air Deflector, Lower Rear ........................................ 220979
Wire Harness Assembly .......................................... 155604
Air Deflector, Top ....................................................... 220978
Hinge Bolt, M6 x 130 mm Hex Hd . ..................... 118033
Fender Washer .250 x 1.500dia............................. 118029
Spacer, .375 o.d. x 3.172 ......................................... 118040
Spacer, .375 o.d x .172............................................... 118039
Ember Stones, 4 oz. * (included in Logset).......... 220702*Orifice Retainer......................................................... 221367*not illlustrated

Accessories

Antique Brick Panel Kit ...........................................................155648
Variable Speed Blower ............................................................155620

Fuel Conversion Kit to Propane.............................................. 155592
Fuel Conversion Kit to Natural Gas....................................... 155593

High Altitude Kit, NG............................................................... 155649
Screen ...........................................................................................129174

Wall Thermostat...................................................................... 750003
Remote Control........................................................................ 750002

Floor Bracket Kit.......................................................................750304		
Torx T20 screwdriver................................................................ 110002

4 mm Allen wrench..................................................................129646

25

137945_Rev_F 7.29.10

Jøtul Gas Product
Limited WarrantyThis warranty policy applies to gas products identified
by Jøtul, Scan, and Atra trade names, as set forth below.
A. Cast Iron, Steel Doors, Surround Components, Firebox:
Jøtul North America Inc. (JØTUL) warrants, to the originalretail purchaser, that those components of the Jøtul, Scan,or Atra Gas Stove or Fireplace specified above will be freeof defects in material and workmanship for a period offive (5) years from the date of purchase. This warranty is
subject to the terms, exclusions and limitations set forthin the following text.
B. Burner, Burner Treatments, Firebox Panels:JØTUL warrants, to the original retail purchaser, thatthose components of the Jøtul, Scan, or Atra Gas Stoveor Fireplace specified above will be free of defects inmaterial and workmanship for a period of two (2) years
from the date of purchase. This warranty is subject tothe terms, exclusions, and limitations set forth in thefollowing text
C. Gas & Electrical Components (controls, plumbing,valve, blower):JØTUL warrants, to the original retail purchaser, thatthose components of the Jøtul, Scan, or Atra Gas Stoveor Fireplace specified above will be free of defects inmaterial and workmanship for a period of one (1) year
from the date of purchase. This warranty is subject tothe terms, exclusions, and limitations set forth in thefollowing text.
JØTUL will repair or replace (including parts & labor), at its option, anyof the above components determined by JØTUL to be covered by thiswarranty. You must, at your own expense, arrange to deliver or ship thecomponent to an authorized Jøtul, Scan, or Atra dealer and arrange for
pickup or delivery of the component after repairs have been made. If,
upon inspection, JØTUL determines that the component is covered bythis warranty, the repair or replacement will be made as set forth above.
This warranty is not transferable and is extended only to, and is solely
for the benefit of, the original retail purchaser of the Jøtul, Scan, orAtra Gas Stove or Fireplace. This paragraph sets forth the sole remedy
available under this warranty in the event of any defect in the Jøtul,Scan, or Atra Gas Stove or Fireplace.
The warranty period for any replaced component will be the remaining
unexpired portion of the warranty period for the original component.
Please retain your dated sales receipt in your records as proof ofpurchase.
EXCLUSIONS AND LIMITATIONSNOTICE: This warranty is void if installation or service is performedby someone other than an authorized installer, service agency or gas
supplier, or if installation is not in conformance with the installationand operating instructions contained in this owner’s manual or
local and/or national fire and building regulations. A listing of local
authorized installers, service agencies and gas suppliers can be obtained
from the National Fireplace Institute at http://www.nficertified.org/.
This warranty does not cover the following:
1) Repair or replacement of parts that are subject to normal wear
and tear during the warranty period or to parts that may require
replacement in connection with normal maintenance. These parts
include gaskets and glass (except to the extent such parts suffer
damage from thermal stress).
2) Damage due to incorrect installations not in conformance with the
installation instructions contained in this owner’s manual or local and/or national fire and building regulations.

263) Damage due to service performed by an installer, service agency or gas
supplier, unless otherwise agreed to in writing by JØTUL.
4) Labor or other costs associated with the repair of gas controls,
plumbing, burners, log set, or sheet metal firebox beyond the warranty
period.
5) Damage caused by unauthorized modification, use or repair.
6) Damage to enameled surfaces caused by improper operation or
misuse, including use that is not in conformance with the operating
instructions contained in this owner’s manual. Such damage can typicallybe identified by bubbling, cracking, or discoloration of the enamel finish.
7) Costs incurred by travel time and/or loss of service.
8) Damage incurred while the Jøtul, Scan, or Atra Gas Stove or Fireplace isin transit.
IN NO EVENT SHALL JØTUL, ITS PARENT COMPANY, SHAREHOLDERS,AFFILIATES, OFFICERS, EMPLOYEES, AGENTS OR REPRESENTATIVES BE
LIABLE OR RESPONSIBLE TO YOU FOR ANY SPECIAL, INDIRECT, INCIDENTAL,CONSEQUENTIAL, PUNITIVE OR OTHER SIMILAR DAMAGES, INCLUDING,
BUT NOT LIMITED TO, LOST PROFITS, LOST SALES, INJURY TO PERSON OR
PROPERTY, OR DAMAGES TO A STRUCTURE OR ITS CONTENTS, ARISINGUNDER ANY THEORY OF LAW WHATSOEVER. ALL IMPLIED WARRANTIES,INCLUDING THE IMPLIED WARRANTIES OF MERCHANTABILITY AND
FITNESS FOR A PARTICULAR PURPOSE, OR OTHERWISE, ARE LIMITED IN
DURATION TO THE LENGTH OF THIS WRITTEN WARRANTY. EXCEPT AS
EXPRESSLY SET FORTH HEREIN, JØTUL MAKES NO ORAL, WRITTEN OR
OTHER WARRANTY WITH RESPECT TO JØTUL, SCAN OR ATRA GAS STOVESOR FIREPLACES.
Some states do not allow the exclusion or limitation of incidental
or consequential damages, or limitations on the length of implied
warranties. Therefore, the above exclusions or limitations may not apply
to you. This warranty gives you specific legal rights, and you may haveother rights, which vary from state to state.
JØTUL reserves the right to discontinue, modify or change the materials
used to produce the Jøtul, Scan, or Atra Gas Stove or Fireplace. JØTUL
shall have the right to replace any defective component with substitutecomponents determined by JØTUL to be of substantially equal quality andprice.
The dollar value of JØTUL’s liability for breach of this warranty shall belimited exclusively to the cost of furnishing a replacement component.
JØTUL shall not in any event be liable for the cost of labor expended
by others in connection with any defective component. Any costs or
expenses beyond those expressly assumed by JØTUL under the terms ofthis warranty shall be the sole responsibility of the owner(s) of the Jøtul,Scan, or Atra Gas Stove or Fireplace.
No dealer, distributor, or other person is authorized to modify, augment,
or extend this limited warranty on behalf of JØTUL. NO MODIFICATION
OR CHANGE TO THIS WARRANTY WILL BE EFFECTIVE UNLESS IT IS MADE IN
A WRITTEN DOCUMENT MANUALLY SIGNED BY AN AUTHORIZED OFFICER
OF JØTUL.
An authorized installer may have been provided with certain information
related particularly to the Jøtul, Scan, or Atra Gas Stove or Fireplace;
however, no authorized installer or other person who may service theappliance is an agent of JØTUL. No inference should be made that JØTUL
has tested, certified, or otherwise pronounced any person as qualified
to install or service the appliance. JØTUL shall not be liable or otherwise
responsible for any error or omission by a person installing or servicing aJøtul, Scan, or Atra Gas Stove or Fireplace.
If you believe your Jøtul, Scan, or Atra Gas Stove or Fireplace is defective,
you should contact your nearest authorized Jøtul, Scan, or Atra dealer,
who will process a warranty claim. IN ORDER TO QUALIFY FOR WARRANTY
COVERAGE, JØTUL MUST RECEIVE NOTICE OF A POSSIBLE DEFECT WITHINSIXTY (60) DAYS OF THE DATE THE DEFECT IS FIRST DISCOVERED, OR
REASONABLY COULD HAVE BEEN DISCOVERED.
This warranty is given by Jøtul North America, Inc.,
55 Hutcherson Drive, Gorham, Maine 04038 USA

LIGHTING INSTRUCTIONS

137945_Rev_F 7.29.10

FOR YOUR SAFETY, READ BEFORE LIGHTING.
WARNING:IF YOU DO NOT FOLLOW THESE INSTRUCTIONS EXACTLY, A FIRE OR EXPLOSION MAY RESULT CAUSING PROPERTY DAMAGE, PERSONAL INJURY, OR LOSS OF LIFE.
A. This appliance has a pilot which must be lit
by hand. When lighting the pilot, follow these
instructions exactly.

B. BEFORE LIGHTING, smell all around the appliance area for gas. Be sure to smell next to thefloor because some gas is heavier than air andwill settle to the floor.
WHAT TO DO IF YOU SMELL GAS:
• Extinguish any open flame.
• Open windows.
• Do not light any appliance.
• Do not touch any electrical switches.
• Do not use any phone in your building.
• Immediately call your gas supplier from aneighbor’s phone.

• If your gas supplier cannot be reached, call thefire department.
C. Use only your hand to push in or turn the gas
control knob. Never use tools. If the knob will notpush in or turn by hand, do not try to repair it.
Call a qualified technician. Force or attempted
repair may result in a fire or explosion.
D. Do not use this appliance if any part has been
under water. Immediately call a qualified service
technician to inspect the appliance and to replace any part of the control system and any gas
control which has been under water.

LIGHTING INSTRUCTIONS
1. STOP! Read the safety information above.
2. Access the lower controls.

7. Push in gas control knob slightly and turncounterclockwise
to “PILOT”.

PILOT

3. Turn the stove ON/OFF switch to “OFF”, or set the 8. Push in control knob all the way and hold in.
Immediately light the pilot by triggering thethermostat to lowest setting (if used).
spark ignitor (push the red button repeatedly)
4. Confirm that the gas supply line shut-off valve isuntil pilot lights. Continue to hold the control
open.
knob in for about one
Control Valveminute after the pilot
lights. Release knob andControlKnob
ON
it should spring back.
The pilot should remain
lit. If it goes out, repeat
Steps 5 through 8.
OFF

5. Push in gas control knob slightly and turn clockwise
to “OFF”.
NOTE: Knob cannot be turned from “PILOT” to“OFF” unless the knob is pushed in slightly. Do
not force.

6. Wait five (5) minutes to clear out any gas. If you
then smell gas, STOP! Follow “B” in the safety
information above on this page. If you do not
smell gas, go to the next step.

• If knob does not
Pilot Assembly
return when released,stop and immediately call your service technician or gas supplier.
• If pilot will not stay lit after several tries,
turn the control knob to OFF and call yourservice technician or gas supplier.

9. Turn gas control knob counterclockwise
to “ON”.

10.Turn the stove ON/OFF switch to “ON”, or set
thermostat (if used) to desired temperature.

TO TURN OFF GAS TO THE APPLIANCE:

1. Turn ON/OFF switch to” OFF”. The pilot willremain lit for normal service.

2. For complete shutdown, turn ON/OFF switch to“OFF”.

3. Access the lower controls.

4. Depress gas control knob slightly and turn clockwise
to OFF”. Do not force.

27

137945_Rev_F 7.29.10

July 2010
137945-F

This appliance must be installed in conformance with local and national building regulations. Before
beginning the installation, it is important that the these instructions be carefully read and understood.
Jøtul maintains a policy of continual product development. Consequently, products may differ in specification, color or type of accessories from those illustrated or described in various publications.
Jøtul vise sans cesse a ameliorer ses produits. C’est pourquoi, il se reserve le droit de modifier les specifications, couleurs etequipement sans avis prelable.

Jøtul ASA
P.O. Box 1411
N-1602 Fredrikstad
NorwayJøtul North America
55 Hutcherson Drive
Gorham, Maine 04038-2634

28