Specification Sheets for:
Direct Expansion Air Conditioning
Chilled Water Air Conditioning
Controls & Accessories
Eskimo Ice Fishbox Ice Systems

L-0002

LB-02

Rev. 20110422

Lit. ID#

Revision Date

Description

Page

DIRECT EXPANSION AIR CONDITIONING
Self-Contained Systems
2502C

07/30/2010

Vector Turbo Self-Contained Series (R-410A)

3

2425C

03/25/2011

Cuddy dc Air Conditioning Kits

5

2620

01/07/2011

Dash Air Low-Profile Self-Contained

7

2769

07/30/2010

R-410A Vector Compact Self-Contained (18K & 27K BTU/hr.)

9

2703A

06/04/2010

Emerald Condenser 6K-16K Series

11

2703B

11/12/2010

Emerald Condenser Multi-Ton Series

13

2696A

09/04/2009

TurboVap DX Evaporator Series

15

2696B

09/04/2009

Emerald TurboVap DX Series

17

2125

08/29/2008

CS Series Condensing Units (6K to 16K BTU/hr Capacity Range)

19

2126

08/29/2008

CS Series Multi-Ton Condensing Units (24K to 60K BTU/hr Capacity Range)

21

2855

01/14/2011

EBE Series R-410A Evaporators

23

2128

01/14/2011

EFD Two-Ton Split Evaporator

25

Split Systems

CHILLED WATER AIR CONDITIONING
2135

04/09/2010

Chiller Compact

27

2735

07/30/2010

MCG Low-Profile R-410A Chillers

29

2734

01/22/2010

MCG Modular Chiller Series

31

2136

01/29/2010

SCW Staged Chilled Water

33

2467

08/29/2008

MTS 25-Ton Chiller

35

2355

12/04/2009

AT Air Handlers for Chilled Water

37

2426A

01/28/2011

Super Quiet AT-DC Air Handlers for CW

39

2546

01/14/2011

ATL Air Handlers for CW

41

2562

05/15/2009

ABL Air Handlers for CW

43

2564

01/07/2011

ATV Air Handlers for CW

45

2404

05/02/2008

AT-MU Fresh Air Make-Up Units

47

2704

09/04/2009

Fresh Air Make-Up & Extraction Units (by Condaria)

49

CONTROLS
2237

09/03/2010

Elite & AH-Elite Digital Control

51

2630

02/04/2011

Passport® I/O Compact Digital Control

53

2133

08/29/2008

Chilled Water Master Controller

55

2345

08/29/2008

CWLC for Chilled Water Systems

57

2701

10/22/2010

In-Duct Breathe Easy™ Air Purifiers

2712

07/30/2010

Portable Breathe Easy™ Air Purifiers

61

2698

08/07/2009

Breathe Easy™ Air Filters

63

2700

01/07/2011

Power Up With SmartStart™

65™

AIR CONDITIONING ACCESSORIES
59

2263

08/13/2010

March Marine Centrifugal Seawater Pumps

67

2129

08/13/2010

Seawater Pumps

69

2134

01/29/2010

Pilot-House Defroster

71

2413

04/22/2011

Variable Frequency Drive

73

2541

04/09/2010

Pump Packages for Chilled Water

75

2130

08/29/2008

Supply & Return Air Grilles

77

2131

08/29/2008

Ducting & Transition Boxes

79

DOMETIC MARINE AIR CONDITIONING
2628

08/06/2010

Dometic EnviroComfort Kits

81

2631

08/06/2010

Dometic EnviroCool Kits

83

2544

04/29/2009

DuraSea Condensing Units

85

2132

07/17/2009

Radome Environmental Control Units

87

ESKIMO ICE SYSTEMS
2450

02/11/2011

Eskimo Ice Ice Systems

89

2617

08/21/2009

Ice Cube Fishbox Ice System

91

N
o
W w
ith Av
R a ila
-4 b
10 le
A

Direct Expansion Systems

Vector Turbo Self-Contained Series

Photo courtesy of Cruisers Yachts

Powerful, Quiet & Compact With No Drain Pan Worries

VTD16K Vector Turbo shownwith optional sound cover

The Vector Turbo series completely revolutionized selfcontained cooling and heating with the newest innovations in marine air
conditioning system design.

Key Benefits■ Up to 27% more energy efficient.
■ Up to 21% increased capacity.

The rust-free molded composite drain pan has three drains for the rapid removal ofcondensate water.

■ Compact design uses less space.
■ Rust-free drain pan.

An advanced cushioning system results in significantly quieter, virtually vibrationfree operation. The enclosed blower motor eliminates overhang to provide easierinstallation.

■ Up to 85% less standing water in drainpan.
■ Reduced noise and vibration with high-velocity blowers and mounts.

The Turbo series was specifically engineered to harness and maximize theimpressive performance of R-410A refrigerant. Used in the HVAC industry for morethan 10 years, R-410A refrigerant is proven, reliable, and complies with all EPA
standards and is accepted world wide.

■ Optional sound cover further reduces

compressor noise by up to 50%.
■ Engineered to maximize performanceof R-410A, an environmentally safe
refrigerant.

Easy-to-install sound cover provides up to 50% noise reduction
Make a quiet system even quieter. These compact, easy-toinstall sound covers are available for all Vector Turbo models.
The cover fits over the compressor, providing a 3- to 5-dB
noise reduction—which is about a 50% drop in what the humanear can perceive. Installation takes just minutes and all mounting
hardware is included.

ISO 9001:2008
L–2502C

Rev. 20100730

Customer comment:“There is very little noise coming from thecompressor, and vibrations are practically
non-existent. I highly recommend this unit.”— Bob Silverman, owner,
305 Bayliner Express Cruiser

3

230
60/1
2.20
2.80
0.36
17.70
0.64
6
8.5/241

115

60/1

4.60

5.90

0.80

36.00

0.68

20

11

8.5/241

Voltage (VAC)

Cycle (Hz)/Phase (Ph) (3)Full Load Amps (FLA) cool

Full Load Amps (FLA) heat

Blower (FLA)

Locked Rotor Amps (Comp)

K.V.A. (Kilo-Volt-Amps)

Max. Circuit Breaker (Amps)

Min. Circuit Ampacity (Amps)

5/127

53.4/24.2

Gross Weight (lbs/kg)

56.7/25.7

46.7/21.2

80/51648/31017.6/447

13.4/3140

Refers to callouts shown in drawing below.

L–2502C Rev. 20100730

Environmentally
Responsible

Specifications and availability subject to change without notice.

International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com†

Notes:(1)
Add a ‘Z’ after the capacity designator for 230V units. Examples VTD8K = 115V, VTD8KZ=230V,
VTD8KZ50=220V/50Hz.
(2)
BTU and electrical data are based on a 45°F / 7.2°C evaporator and 100°F / 37.8°C condenser in cool mode, and a
45°F / 7.2°C evaporator and 130°F / 54.4°C condenser in heat.
(3)
60Hz units must not operate at 50Hz and 50Hz units must not operate at 60Hz unless data plate states otherwise.
(4)
Electric box is remote mounted up to 34" (864 mm) away from compressor. Electrical box dimensions are 2.7"
(69 mm) x 6.5" (165 mm) x 8.8" (224 mm).

64/41343.4/19.7

Min. RA Grille (sq. in./sq. cm.)

Net Weight (lbs/kg)

4/102
32/206

10.7/272

Depth (B†)

Min. Duct Size Ø (in/mm)

17.6/447

Min. SA Grille (sq. in./sq. cm.)

10.7/272

13.4/340

Height – w/opt. Sound Cover

Width (A†)

11.1/282

10.8/274

10.8/274

9.5/269

6

11

0.92

17.70

0.70

4.00

3.10

60/1

230

11.1/282

9.0/255

12

21

0.82

36.00

1.31

7.10

5.50

60/1

115

Height – Compressor (D†)

8.5/241

6

10

0.88

17.70

0.36

3.70

2.70

50/1

240

8,000

VTD8K

Height – Evaporator (C†)

Unit Dimensions (in/mm) (4)Refrigerant R-410A (oz/g)

6,000

Capacity (BTU/Hr)(2)

11

VTD6K

Model(1)Technical Specifications for Vector Turbo Series

B

9.5/269

6

11

0.99

17.70

0.83

4.10

3.20

50/1

240

Seawater inlet

A

12.5/318

11.0/312

8

14

0.91

18.80

0.48

3.80

2.90

50/1

240

Mounting brackets included

59.6/27.0

49.6/22.5

100/645

60/3876/152

12.4/315

20.4/518

14.0/356

12.5/318

12.2/310

11.0/312

9

16

0.90

22.00

0.61

3.90

3.30

60/1

230

C

D

B

Condensate drain fitting included
Seawater outlet

13.0/329

11.0/312

16

27

1.02

42.00

1.14

8.80

6.70

60/1

115

10,000

VTD10K

10.5/298

19

34

1.26

58.00

1.14

10.90

8.70

60/1

115

Dealer:63.0/28.6

53.0/24.0

130/839

70/452

6/152

12.4/315

20.4/518

14.0/356

12.5/318

12.2/310

11.0/312

10

18

1.18

28.00

0.61

5.10

4.00

60/1

230

12,000

VTD12K

11.5/326

8

14

1.03

21.00

0.48

4.30

3.30

50/1

240

13.0/369

24

42

1.57

62.00

1.61

13.60

10.40

60/1

115

69.6/31.6

59.6/27.0

160/1032

80/516

7/178

13.3/338

21.4/544

14.0/356

13.4/340

12.9/328

13.0/369

12

20

1.51

34.00

0.78

6.60

5.10

60/1

230

16,000

VTD16K240

13.0/369

11

20

1.43

22.00

0.56

6.00

4.60

50/1

4
Direct Expansion Systems

Direct Expansion Systems

Cuddy dc Air Conditioning Kits

Photo courtesy of Pro-Line Boats

Easy & Affordable Cold Air for Smaller Cabins

Cuddy dc 3,500
BTU/hr Kit

The Dometic Cuddy dc is a compact 3,500 BTU/hr cool-only air
conditioner designed to work with 12V power systems. Energized by a

Key Benefits

dedicated bank of batteries and a dedicated power module (DPM), the Cuddy dc■ Designed for small cabins.

makes your small cabin a refuge from the heat and sun. Compact—about the size of■ Operates via simple 12V DC connections.

a typical battery box—this low-profile unit easily fits beneath a V-berth or in a storage■ Compact—about the size of a battery box.

area below deck. The Cuddy dc uses R-134A, a globally accepted, environmentally■ High-velocity blower with split capacitor forsafe refrigerant.

greater airflow.
■ Stainless-steel chassis.

Your dedicated 12V DC battery bank powers the system via the Dometic DPM.
Two ABYC-approved wires (sized properly for your unique installation) run from thededicated battery bank to the DPM. Easy-to-use polarized plugs connect the DPM
to the seawater pump and the Cuddy dc unit. Optional cables are available for longer■ Simple two-knob mechanical control

maximizes efficiency and runtime.
■ Minimal DC draw (about 29 DC amps

total).

runs if your setup requires more than the standard 4.5 ft. (1.37 m) cable included with

■ No genset needed.

the kit.

■ Air distribution kits available.

To operate the system, the Cuddy dc uses a simple two-knob mechanical control.
Since it draws no power itself, the mechanical control maximizes runtime andefficiency. The Cuddy dc system (compressor, blower, and pump) draws about 29
amps of DC power under normal operating conditions. Supplemental DC power
comes to you via engine power (if available) or via shore power through a battery
charger.

ISO 9001:2008
L–2425C

Rev. 20110325

5

6

Direct Expansion Systems

Technical Specifications for Cuddy dc Kits
Dimensions (in/mm)
Component

Capacity

Cuddy dc Unit
Dedicated Power Module (DPM)
Control
Seawater Pump

Weight(lbs./kg.)

Refrigerant

Height

Width

Depth

3,500 BTU/hr
N/A

9.25/235
5.13/13015.00/381

8.0/204
2.67/68

29.0/13.2
3.0/1.3

R-134A

10.00/254

N/A

5.50/140

3.25/83

2.75/70——

150 GPH

2.75/70

3.50/89

4.75/121

1.0/0.46—

Electrical(Compressor, Blower,
and PML 150 Pump)—~29 amps (1)(12V DC)

Notes:(1)
Actual load is dependent upon humidity, seawater temperature, battery condition, voltage, and electrical connections.

Cuddy dc Kits & Accessories
Cuddy dc – 12V DC system
Extension cable
Extension cable
Extension cable
Air Distribution Kit – BlackAir Distribution Kit – White

Cooling-only unit, DPM, 150 GPH seawater pump, control, polarized plugs
DPM to Unit - 10' (3m)
DPM to Unit - 20' (6m)
PLM 250 to Unit - 10' (3m)
3" discharge grille - black; 8" X 8" (204mm X 204mm) return grille; 10' (3m) of 3" duct3" discharge grille - white; 8" X 8" (204mm X 204mm) return grille; 10' (3m) of 3" duct

Dedicated Power Module
Our Cuddy dc kit includes a Dedicated Power Module (DPM) that has been Dometic-tested to handle the air conditioning load.
Batteries & Battery Charger
You must provide the right type of batteries and the right type of battery charger. Use only Deep-Cycle AGM or Gel-Cell batteries. (Do not use WetCell batteries.) The battery charger must be rated for the type of battery you use. The Cuddy dc requres a dedicated battery bank. To maximize runtime, we recommend using at least two batteries in the bank. (The more cells, the longer the runtime.) All batteries used must be of the same type
(either all AGM or all Gel Cell), the same capacity, and the same age.

CustomerprovidesPropergauge wire

Disconnect
switchPlug & Play

Dometic
providesDPM
60-amp fuseor breaker

Ded
ica
Batt tederies

Cuddy dc
air conditioner

Battery combiner

Minimum 50-amp
battery charger

EngiBatt neeries

Alternator

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2425C Rev. 20110325

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:No
W w
ith Av
R a ila
-4 b
10 le
A

Direct Expansion Systems

Stay Cool With Dash Air
For Flybridge, Cockpit & On-Deck Installations

VLD16K selfcontained model

Dash Air delivers high-velocity cold air (or HOT!) onto the bridge,
cockpit, or deck using an innovative horizontal compressor. The
16,000 BTU/hr. self-contained package stands just eight inches (203 mm)
high and is easily ducted to confined spaces like flybridge dashboards andconsoles.

Key Benefits■

Innovative horizontal compressor requires
only 8 in. (203 mm) of height for installation.

■

16,000 BTU/hr. in a high-velocity unit.

■

Highly-efficient dual blowers.

■

Flybridge, cockpit and on-deckinstallations.

■

Environmentally safe R-410A refrigerant.

■

304-grade stainless-steel drain pan for longservice life.

■

Stainless-steel condensate drains forexcellent water removal.

All Dash Air systems are reverse-cycle, blowing warm air on chilly days,
thereby extending your cruising season. All units are designed for easy,
professional installation on new boats and older vessels.

■

Condensate under evaporator to minimize
sloshing and remove water rapidly.

■

Remote electrical box with 5 ft. (1.52 m)
harness.

Dash Air features an oversized four-row evaporator coil for excellent heatremoval under low fan-speed conditions. A highly efficient blower reduces
power consumption, and the blower flows to two outlets.

■

Special corrosion-resistant coating on
blower and housing.

■

Oversized four-row evaporator coil for
excellent heat removal under low fanspeed conditions.

Dash Air air conditioning systems use R-410A, an environmentally safe
refrigerant with exceptional thermodynamic properties that maximize systemefficiency.
Also available is a 16,000 BTU/hr. evaporator connected to a remotecondensing unit below decks.

ISO 9001:2008
L–2620Rev. 20110107

7

8

Direct Expansion Systems

Technical Specifications for R-410A Dash Air Systems
Unit TypeCapacity (BTU/hr.)(1)Self-Contained Units
16,000Split Evaporator
16,000Model Number

VLD16K

VLD16KZ

VLD16KZ50

EDLE16-115V

Voltage (VAC)

115

230

240

115

EDLE16-230V
230

Cycle (Hz)/Phase (Ph)(2)

60/1

60/1

50/1

60/1

Blower Amps

2.00

0.86

0.62

2.00

60/1 & 50/1
0.86 @ 230V/60Hz
0.62 @ 230V/50Hz

Full Load Amps (FLA) cool

11.0

4.7

4.5

N/A

Full Load Amps (FLA) heat

14.2

6.2

5.8

N/A

Locked Rotor Amps (Comp)

61

29

26

K.V.A. (Kilo-Volt-Amps)

1.63

1.42

1.40

0.23

0.20

Max. Circuit Ampacity (Amps)

35

20

20

5

4

Min. Circuit Ampacity (Amps)

23

14

13

3

2

16.0/454

15.0/425

15.5/439

N/A

N/A

Refrigerant R-410A (oz/g)

N/A

Dimensions (in/mm)
Height8.00/203

7.40/188

Width

30.25/768

22.25/566

Depth

14.00/356

11.00/280

Min. Duct Size Ø

7.0/178

7.0/178Min. SA Grille (sq. in./cm.)

80/51680/516

Min. RA Grille (sq. in./cm.)

160/1032

160/1032

Net Weight (lbs/kg)

70/15419/9

Gross Weight (lbs/kg)

80/176

29/13

(1)
(2)

BTU and electrical data are based on a 45°F (7.2°C) evaporator and 100°F (37.8°C) condenser in cool mode, and a 45°F (7.2°C) evaporator and 130°F (54.4°C) condenser in heat mode.
Note: 60Hz units must not operate at 50Hz and 50Hz units must not operate at 60Hz unless data plate says otherwise.

Available Custom Air Flow Accessories:#229000005#229000006#229000007#228700089

PLNM AMN RA VLD16/2@5" Side Discharge Plenum
PLNM AMN RA VLD16/2@5" Upward Discharge Plenum
PLNM AMN RA VLD16/2@5" Downward Discharge Plenum
Ring ABS trans 5"-OB Short Flange

Discharge Air

7.97" (203mm)

2.48" (63mm)

4.69" (119mm)

Dimensions for Self-Contained Dash Air

4.63" (118mm)
X20.94" (24mm)
14.00" (356mm)

13.35" (339mm)
22.63" (575mm)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2620 Rev. 20110107

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Direct Expansion Systems

9

R-410A Vector Compact®

18K & 27K BTU/hr Self-Contained Systems

VCD27K-HV-410A

The Vector Compact series of self-contained marine air
conditioners offers 18K and 27K BTU/hr of cooling and

Key Benefits

heating.

■ Compact design reduces unit size by up to

These high-capacity units were engineered to harness and maximize the impressive■ High-velocity, fully-insulated blowers.

performance of environmentally safe R-410A refrigerant. Used in the HVAC industry■ Fully rotatable blowers.

for more than 10 years, R-410A refrigerant is proven and reliable, and complies with all■ Patented design increases cooling capacity

EPA standards and is accepted worldwide.
All models offer direct expansion operation in a compact, low-profile unit, with aseawater-cooled condenser and choice of controls. Vector Compact units aredesigned for installation under a settee or berth, in a locker or cabinet, or otherconvenient location.

25% of the original Vector Rotary’s size.

and dehumidification.
■ Unique compressor and reversing valve

mounting reduces vibration.
■ Electrical box installed on unit withinfootprint dimensions eliminates additional
installation labor and space requirements.
■ High-efficiency rotary (18K) and scroll (27K)

Vector Compact systems feature high-velocity (HV) blowers. All blowers are insulated
to prevent secondary condensation, and are fully rotatable for flexibility during
installation.

compressors are quiet and more reliable.
■ Condenser coil’s cupronickel-encased

copper shell provides maximum heattransfer and high corrosion resistance.
■ Evaporator coil employs an enhanced fin

design and rifled copper tubing to provide
maximum capacity.

ISO 9001:2008
L–2769Rev. 20100730

10

Direct Expansion Systems

Technical Specifications for R-410A Vector Compact®
Model(1)Capacity BTU/hr(2)Voltage (VAC)
Cycle (Hz)/Phase (Ph)(3)Full Load Amps (FLA) Cool
Full Load Amps (FLA) Heat
Locked Rotor Amps (Comp)
Kilo-Volt-Amps (KVA)
Max. Circuit Breaker (Amps)
Min. Circuit Ampacity (Amps)
R-410A Refrigerant (oz/kg)
Height – Evaporator (in/mm)
Height – Blower (in/mm)(4)Width (in/mm)
Depth (in/mm)
Motor Overhang (in/mm)
Min. Duct Size Ø (in/mm)
Min. Supply Grille (in2/cm2)
Min. Return Grille (in2/cm2)
Net Weight (lbs/kg)
Gross Weight (lbs/kg)

115
60/1
11.1
15.1
66.0
1.8
45.0
27.0

VCD18K/1-HV-410A
18,000208-230
60/1
6.1
8.0
32.0
1.9
20.0
12.0
17.0/0.482
14.00/356
15.50/394
12.00/305
21.00/533
1.00/25(5)7.00/178
100.00/645
200.00/1290
63.8/28.9
73.0/33.1

Notes:(1)
VCD indicates Elite or Passport I/O climate controls; VCM indicates mechanical controls.
(2)
BTU and electrical data are based on a 45°F/7.2°C evaporator and 100°F/37.8°C condenser in coolmode, and a 45°F/7.2°C evaporator and 130°F/54.4°C condenser in heat.
(3)
60Hz units must not operate at 50Hz and 50Hz units must not operate at 60Hz unless data plate
states otherwise.
(4)
Height with blower in the horizontal position. Overall height can be reduced by rotating blower
downward.
(5)Motor is inside blower on HV units. However, allow 1.00"/25mm for blower ring flange on that side.

220-240
50/1
5.5
6.8
26.0
1.6
20.0
12.0
16.5/0.468

VCD27K-HV-410A
27,000208-230220-240
60/1
50/1
7.9
9.0
11.1
12.6
58.3
61.0
2.6
3.1
45.0
45.0
27.0
26.0
23.5/667.0
23.0/652.0
18.00/457
19.25/489
15.25/387
24.75/629
N/A
8.00/203
140.00/903
240.00/1548
120.0/54.4
130.0/58.9

Transition Box

Supply Air Grille

Patented design:
Condenser coil insideevaporator shroud

Elite or Passport I/O
display panel used with
VCD models; VCM
models use a 3-knob
mechanical control

Flexible
ducting
Height

Width

Depth

Display
cable

Vector Compact®
self-contained air
conditioning unit
(blower rotated tovertical position)

Return air
grilleElectric box
on unit
Mounting
brackets
Condensate
drain

Handle built into
condensate pan

Seawaterpump
Seawaterstrainer

Overboarddischarge
Thru-hull fitting(clam shell scoop

Shut-off valve

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2769 Rev. 20100730

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:

11

Emerald Condenser 6K-16K Series
Innovative Chassis Conquers Installation Challenges

Photo courtesy of Viking Yachts

N

E
W
!

Direct Expansion Systems

ED12 shown

After listening to boat builders, global service teams and boat owners,
Dometic engineers designed a totally innovative Emerald Condenser
series to harness and maximize the impressive performance of R-410A
refrigerant while meeting all international clean air standards.
The increase in BTU capacity is due primarily to the improved refrigerant metering
design. The bi-flow thermal expansion valve for cooling provides up to a 14% increase insystem capacity, which, when combined with a separate metering system for heating,attains an increase of up to 10% in heating performance. The amperage reduction of up
to 27% is due to the more efficient design of the rotary compressor and properly sizedrefrigerant components.
The Emerald Condenser has a minimized footprint. This compact design incorporates
built-in isolation, two large drain connections and numerous mounting options for
installation to a smooth deck, stringer or existing rack. The incorporated lifting handles
and smooth bottom allows for easy lifting and quick placement of the unit.The moldedcomposite no-rust drain pan is shaped to provide positive drainage even when the boatheaves and rolls. The amount of standing water in the drain pan is reduced by up to 85%,
which is 8x times less than a typical drain pan.
The condensing unit provides quick and easy installation. The drain, seawater andrefrigerant connections are conveniently located to conquer installation challenges
thus reducing installation time by up to fifteen minutes. The electrical box can be easily
removed and located up to 5 ft. (1.5 m) away, further reducing the size of the unit
while making the system more accessible. The reversing valve, pressure switches andservice ports are centrally located, high on the unit for access from any side.

ISO 9001:2008
L–2703A

Rev. 20100604

Key Benefits■ Up to 17.5% increase in BTU capacity.
■ Up to 41% amperage reduction.
■ Up to 32% reduced start-up amps.
■ Up to 16% smaller.
■ Up to 25% lighter.
■ Up to 85% reduction in condensate in thedrain pan.
■ Up to 15 minutes faster to install.
■ Square chassis for easy installation in tightlocations.
■ Three mounting options adapt toinstallation environments.
■ Composite drain pan will not rust.
■ Reconfigurable chassis allows optimal

drain connection locations.
■ Built-in refrigerant-line filter drier reduces

installation time and protects compressor
from moisture and contaminants.
■ High-performance engineering maximizes

the efficiency of R-410A refrigerant.
■ Available in capacities ranging from 6K to

48K BTU/hr.

240/50/1
2.4
3.3
17.7
10.0

115/60/1
4.2
5.8
36.0
20.0

43.0/19.5
50.0/22.7

5/8" hose clamp
1/4"
3/8"

12.0/305
13.3/338
13.3/338
15.1/384ED8
8,000
230/60/1
2.4
3.3
17.7
10.0
R-410A
2.0/7.6

Width

HeightL–2703A Rev. 20100604

Specificiations and availability subject to change without notice.

International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com

Depth 2Depth 1* Please refer to spec sheet L-2703B for the Emerald Condenser 24K-48K Series.

Environmentally
Responsible

Depth240/50/1
2.4
3.3
18.8
10.0

Made in the USA

WidthElectrical Box(when mounted remotely)

ED10
10,000240/50/1
115/60/1
230/60/1
2.4
5.6
2.6
3.3
7.7
3.3
17.7
42.0
22.0
10.0
30.0
10.0
R-410A
2.5/9.5
Unit Dimensions (in/mm)
13.0/330
13.3/338
13.3/338
15.1/384
Connections Ø
5/8" hose clamp
1/4"
3/8"
Weights (lbs./kg.)
45.0/20.4
52.0/23.6

Notes:(1)
ED models have a Passport I/O control. For units with a mechanical control, replace the “D” with “M”, e.g. “EM16”.
(2)
Actual unit depth when electrical box is mounted remotely.
(3)
Combined depth of unit and electrical box, as shown in the drawing below.

43.0/19.5
50.0/22.7

5/8" hose clamp
1/4"
3/8"

Sea Water (in. and type)
Discharge
Suction

Net Weight
Gross Weight

12.0/305
13.3/338
13.3/338
15.1/384

115/60/1
3.8
5.1
36.0
20.0

ED6
6,000
230/60/1
1.8
2.4
17.7
10.0
R-410A
1.5/5.7

HeightWidth
Depth 12
Depth 2 (w/elec. box)3

Model(1)Capacity (BTU/Hr)
Power (Volt/Hz/Ph)
Full Load Amps (FLA) – Cool
Full Load Amps (FLA) – Heat
Locked Rotor Amps
Max. Circuit Breaker (Amps)
Refrigerant Type
Seawater Flow (gpm/lpm)

Technical Specifications for Emerald Condenser 6K-16K Series

Height115/60/1
7.6
9.8
58.0
35.0

240/50/1
2.8
3.8
21.0
10.0

115/60/1
8.8
12.0
62.0
45.0

49.0/22.2
56.0/25.4

Dealer:Height8.75/222

Width
6.50/165

240/50/1
4.0
5.3
22.0
15.0

Depth
2.63/67

5/8" hose clamp
1/4"
1/2"

14.1/358
13.3/338
13.3/338
15.1/384

ED16
16,000230/60/1
4.3
5.8
34.0
15.0
R-410A
4.0/15.1

Electrical Box Dimensions (in/mm)

47.0/21.3
54.0/24.5

5/8" hose clamp
1/4"
3/8"

13.0/330
13.3/338
13.3/338
15.1/384

ED12
12,000230/60/1
3.4
4.5
28.0
15.0
R-410A
3.0/11.4

12
Direct Expansion Systems

N

E
W
!

Direct Expansion Systems

13

Emerald Condenser Multi-Ton Series
Innovative Chassis Conquers Installation Challenges

ED30 shown

After listening to boat builders, global service teams and boat owners,
Dometic engineers designed a totally innovative Emerald Condenser
series to harness and maximize the impressive performance of R-410A
refrigerant while meeting all international clean air standards.

Key Benefits■ Up to 85% reduction in condensate

drainage.
■ Up to 15 minutes faster to install.

The Emerald Condenser has a minimized footprint. This compact design incorporates■ Reduced amps.

built-in isolation, two large drain connections and numerous mounting options for■ Square chassis for easy installation in tightinstallation to a smooth deck, stringer or existing rack. The incorporated lifting handles
and smooth bottom allows for easy lifting and quick placement of the unit.The moldedcomposite no-rust drain pan is shaped to provide positive drainage even when the boat

locations.
■ Three mounting options adapt toinstallation environments.

heaves and rolls. The amount of standing water in the drain pan is reduced by up to■ Composite drain pan will not rust.

85%, which is 8x times less than a typical drain pan.

■ Built-in refrigerant-line filter drier reduces

The condensing unit provides quick and easy installation. The drain, seawater andrefrigerant connections are conveniently located to conquer installation challenges thus
reducing installation time by up to fifteen minutes. The electrical box can be removed
and located up to 5 ft. (1.5 m) away, further reducing the size of the unit while making
the system more accessible. The reversing valve, pressure switches and service ports
are centrally located, high on the unit for access from any side.

ISO 9001:2008
L–2703B

Rev. 20101112

installation time and protects compressor
from moisture and contaminants.
■ High-performance engineering maximizes

the efficiency of R-410A refrigerant.
■ Available in 11 capacities from 6K to 72K

BTUs/hr. (For 6K-16K data, please refer tospecification sheet L-2703A.)

230
60/1
6.3
7.8
43.0
1.79
30
20

110/50.0
125/56.8

3/8"
5/8"

18.0/457
16.0/406
16.0/406
18.8/478

ED24
24,0000
240
230
50/1 60/3
6.8
4.9
8.6
6.6
48.0 55.0
2.06 2.63
32
25
20
15
42/1191

460
60/3
2.4
3.2
22.4
2.55
15
10

380
50/3
2.7
3.6
28.0
2.37
15
10

230
60/1
7.3
9.2
54.0
2.12
35
25

115/52.3
130/59.1

3/8"
3/4"

18.0/457
16.0/406
16.0/406
18.8/478

ED30
30,0000
240
230
50/1 60/3
8.0
5.4
10.4
7.3
64.0 58.0
2.50 2.90
35
30
25
20
48/1361
460
60/3
2.7
3.6
28.0
2.86
15
10

380
50/3
3.2
4.2
38.0
2.76
15
10

230
60/1
9.1
11.5
74.0
2.65
45
30

ED36
36,000
240
230
460
380
50/1 60/3 60/3 50/3
9.4
6.3
3.3
4.4
12.2
8.3
4.2
5.9
64.0 71.0 38.0 45.0
2.93 3.30 3.34 3.88
40
30
15
20
35
20
10
15
56/1588
Unit Dimensions (in/mm)
18.0/457
16.0/406
16.0/406
18.8/478
Connections Ø
3/8"
3/4"
Estimated Weights
120/54.5
135/61.4

L–2703B Rev. 20101112

Environmentally
Responsible

Specifications and availability subject to change without notice.

International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com* Please refer to spec sheet L-2703A for the Emerald Condenser 6K-16K Series.

Notes:(1)
ED units have a Passport I/O control. For units with a mechanical control, replace the “D” with “M”, e.g. “EM24”.
(2)
BTU and electrical data are based on a 45°F/7.2°C evaporator and 100°F/37.8°C condenser in cool mode, and a 45°F/7.2°C evaporator
and 130°F/54.4°C condenser in heat.
(3)
60Hz units must not operate at 50Hz and 50Hz units must not operate at 60Hz unless data plate says otherwise.
(4)
Refrigerant charges shown are for R-410A.
(5)
Combined depth of unit and electrical box, as shown in the drawing below. For remote mounting, the electrical box dimensions are
13.25" high X 7.75" wide X 3.75" deep (337 mm X 197 mm X 95 mm).

Net Weight (lbs/kg)
Gross Weight (lbs/kg)

Refrigerant Line – Discharge
Refrigerant Line – Suction

HeightWidth
Depth 1
Depth 2(5)Model(1)Capacity (BTU/Hr)(2)Voltage (VAC)
Cycle (Hz)/Phase (Ph)(3)Full Load Amps (FLA) – Cool
Full Load Amps (FLA) – Heat
Locked Rotor Amps (Comp)
K.V.A. (Kilo-Volt-Amps)
Max. Circuit Breaker (Amps)
Min. Circuit Ampacity (Amps)
Refrigerant R-410A (oz/g)(4)
380
50/3
4.2
5.7
60.0
3.75
30
20

Depth 1

460
60/3
3.8
5.0
45.0
3.98
20
15

Depth 2135/61.4
150/68.2

3/8"
3/4"

18.5/470
16.0/406
16.0/406
18.8/478

ED48
48,000230240
230
60/1 50/1 60/3
11.9 12.1
8.2
15.7 17.9 10.9
105.0 115.0 95.0
3.61 4.30 4.34
70
70
50
45
45
30
64/1814

Technical Specifications for Emerald Condenser Multi-Ton Series

Dealer:150/68.2
165/75.0

3/8"
3/4"

20/50816/406
16/40618.8/478

ED60
60,000230240
230
60/1 50/1 60/3
13.6 14.4 10.2
20.2 21.4 12.7
150.0 130.0 120.0
4.65 5.14 5.05
80
80
55
50
50
35
70/1984
460
60/3
5.3
6.6
60.0
5.25
30
20

380
50/3
5.6
7.6
70.0
5.00
30
20

Width

155/70.5
170/77.3

3/8"
3/4"

20/50816/406
16/40618.8/478

ED72
72,000230240
230
60/1 50/1 60/3
15.5 21.5 11.2
23.0 29.1 14.8
145.0 130.0 123.0
5.29 6.98 5.89
90
90
60
60
60
35
76/2155
460
60/3
6.0
7.4
70.0
5.89
30
20

Height

380
50/3
8.0
10.8
87.0
7.10
40
25

14
Direct Expansion Systems

15

TurboVap DX Evaporator Series

Reduced Size, Noise & Amperage

Photo courtesy of Viking Yachts

N

E
W
!

Direct Expansion Systems

TV12-230V shown

Marine Air’s TurboVap Series of direct expansion (DX) split-systemevaporators is based on the revolutionary engineering advancements of
the award-winning Turbo self-contained air conditioning system. Featuring
a rust-free molded composite drain pan, condensate water is rapidly removed at oneof two easy-to-plumb drain locations. The pan also has innovatively designed anti-slosh
ridges and “positive flow” channels to ensure condensate does not spill even in theroughest seas.
For improved installation ease and flexibility, the enclosed blower motor eliminates
overhang and the blower can be rotated 270° with a single adjustment screw. The unit’s
unique inlet ring is designed to optimize air flow and ensure that the height of the unit
does not increase when the blower rotates. The fully insulated, high-velocity blowers
are quiet and efficient.
Experience better noise reduction with the TurboVap Series’ built-in cushioning system
which minimizes vibration to the deck. Additionally, the innovative mounting clips utilize
vibration isolators.
TurboVap units can be paired with condensers that use either R-22 or R-417A
refrigerants. See the Emerald Series of TurboVaps and condensers for a complete split
system that uses R-410A refrigerant.

Key Benefits■ Up to 28% reduced amperage.
■ Up to 85% reduction of standing water inthe drain pan.
■ Up to 14% increase in cooling capacity.
■ Up to 15% reduced weight.
■ Up to 17% reduction in height.
■ Up to 19% increased air flow CFM.
■ Positive-flow, anti-slosh, rust-free drain pan

ensures condensate does not spill.
■ Installation time reduced by 15 minutes.
■ Single screw for 270° blower rotation.
■ No blower-motor overhang reduces depth.
■ Vibration-isolation mounting system

reduces noise.
■ Available in 4K, 6K, 8K, 10K, 12K, and 16K

BTU/hr capacities.
■ 115V or 230V models.
■ Pair with R-22 or R-417A condensing units.

Rust-free molded composite drain pan reduces
standing water – 2 oz. (59 ml) vs. 16 oz. (473 ml)
in ordinary pans. Innovatively engineered “positiveflow” drain channels prevent the sloshing andspilling of condensate — even in the roughest seas.
ISO 9001:2008
L–2696A

Rev. 20090904

16

Direct Expansion Systems

Technical Specifications for TurboVap DX Evaporators
Model(1)

TV4

TV6

TV8

TV10

TV12

TV16

Capacity BTU/hr

4,000

6,000

8,000

10,00012,00016,000

Voltage (VAC)@ 50-60Hz/1 Ph
Full Load Amps Blower
(FLA)

115

230

115

230

115

230

115

230

115

230

115

230

0.8

0.41

0.8

0.41

1.56

0.83

1.14

0.61

1.14

0.61

1.61

0.78

K.V.A. (Kilo-Volt-Amps)

0.09

0.09

0.09

0.09

0.18

0.19

0.13

0.14

0.13

0.14

0.19

0.18

Suggested Circuit Breaker(Amps)

2.0

1.0

2.0

1.0

4.0

2.0

3.0

1.0

3.0

1.0

4.0

2.0

Unit Dimensions (in/mm)
Height – Evaporator (H1)

10.8/274

10.8/274

10.8/274

12.6/32012.6/32013.0/330

Height – Blower (H2)(2)

10.2/259

10.2/259

11.4/29012.4/31512.4/31513.6/345

Width12.3/312

12.3/312

12.3/312

14.3/363

14.3/363

14.3/363

Depth

9.5/241

9.5/241

9.4/239

10.4/26410.4/26411.6/295

Min. Duct Size Ø

4.0/102

4.0/102

5.0/127

6.0/152

6.0/152

7.0/178

32/20632/20648/31060/38770/45281/52364/41364/41380/516

110/710130/839

160/1032

Net Weight (lbs./kg.)

10.5/4.8

11.0/5.0

14.0/6.4

17.5/7.9

17.5/7.9

20.5/9.3

Gross Weight (lbs./kg.)

18.5/8.4

19.0/8.6

22.0/10.0

25.5/11.6

25.5/11.6

28.5/12.9

Min. Supply Air Grille(sq. in./cm.)
Min. Return Air Grille(sq. in./cm.)

Notes:(1)(2)

Supply-Air Grille

Typical Installation ofa Split A/C System

End all model numbers with a ‘115V’ or ‘230V’ depending on the selected voltage.
Add 2.0"/51mm to the height dimension to allow for the duct ring (not included) when theblower is installed in the vertical position.

Flexibleduct

H2Electrical Box

H1Return-Air Grillewith Filter

Display Panel
Condensate
Drain

Condensing Unit
W

Transition Box

DCondensate Drain
Sea-Water Inlet

Sea-Water
OutletSea-Water Pump

Insulated Copper Line Set

Evaporator/Blower
Assembly (Air Handler)

Shut-off Valve

Sea-Water Strainer
Overboard Discharge

Thru-hull Fitting(Clam Shell Scoop)

TurboVap 12K unit shown with
optional lineset extensions.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
United States & Canada Tech Support
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2696A Rev. 20090904

Environmentally
Responsible

Specificiations and availability subject to change without notice.

Dealer:

17

Emerald TurboVap DX Series

N

E
W
!

Direct Expansion Systems

Reduced Size, Noise & Amperage

TVE12-230V shown

The Emerald TurboVap series of split-system evaporators incorporates
revolutionary design features with mechanical engineering thatmaximizes the effectiveness of R-410A, an environmentally safe
refrigerant.
Emerald TurboVaps are easy to install. For ideal positioning, the high-velocity blower canrotate up to 270 degrees with a single adjustment screw. The enclosed motor meansno blower-motor overhang for a compact design.
Since evaporators are usually positioned in or near cabins, noise is always a concern.
The Emerald TurboVap uses a vibration-isolation mounting system to minimize noise, so
the evaporator runs more quietly. The fully insulated, high-velocity blowers are quiet andefficient.
Excellent condensate drainage is achieved with a unique positive-flow, anti-slosh,composite drain pan that is rust-free. Condensate water is rapidly removed at one of
two easy-to-plumb drain locations.
The Emerald TurboVap Series was designed to operate as a system with the Emerald
Condenser Series. Both of these split-system components were engineered to harness
and maximize the superior thermodynamic properties of the environmentally safe
R-410A refrigerant.
The Emerald TurboVap is available in six capacities ranging from 4,000 to 16,000 BTU/hr.

Key Benefits■ Up to 28% reduced amperage.
■ Up to 85% reduction of standing water inthe drain pan.
■ Up to 14% increase in cooling capacity.
■ Up to 15% reduced weight.
■ Up to 17% reduction in height.
■ Up to 19% increased air flow CFM.
■ Positive-flow, anti-slosh, rust-free drain pan

ensures condensate does not spill.
■ Installation time reduced by 15 minutes.
■ Single screw for 270° blower rotation.
■ No blower-motor overhang reduces depth.
■ Vibration-isolation mounting system

reduces noise.
■ Pair it with an Emerald Condenser for

maximum performance.
■ Available in 4K, 6K, 8K, 10K, 12K, and 16K

BTU/hr capacities.
■ 115V or 230V models.

Rust-free molded composite drain pan reduces
standing water – 2 oz. (59 ml) vs. 16 oz. (473 ml) in
ordinary pans. Innovatively engineered “positive flow”
drain channels prevent the sloshing and spilling ofcondensate — even in the roughest seas.
ISO 9001:2008
L–2696B

Rev. 20090904■ Engineered to maximize thermodynamic

properties of R-410A, an environmentallysafe refrigerant.

18

Direct Expansion Systems

Technical Specifications for Emerald TurboVap DX Evaporators
Model(1)

TVE4

TVE6

TVE8

TVE10

TVE12

TVE16

Capacity BTU/hr

4,000

6,000

8,000

10,00012,00016,000

Voltage (VAC)@ 50-60Hz/1 Ph
Full Load Amps Blower
(FLA)

115

230

115

230

115

230

115

230

115

230

115

230

0.8

0.41

0.8

0.41

1.56

0.83

1.14

0.61

1.14

0.61

1.61

0.78

K.V.A. (Kilo-Volt-Amps)

0.09

0.09

0.09

0.09

0.18

0.19

0.13

0.14

0.13

0.14

0.19

0.18

Suggested Circuit Breaker(Amps)

2.0

1.0

2.0

1.0

4.0

2.0

3.0

1.0

3.0

1.0

4.0

2.0

Unit Dimensions (in/mm)
Height – Evaporator (H1)

10.8/274

10.8/274

10.8/274

12.6/32012.6/32013.0/330

Height – Blower (H2)(2)

10.2/259

10.2/259

11.4/29012.4/31512.4/31513.6/345

Width12.3/312

12.3/312

12.3/312

14.3/363

14.3/363

14.3/363

Depth

9.5/241

9.5/241

9.4/239

10.4/26410.4/26411.6/295

Min. Duct Size Ø

4.0/102

4.0/102

5.0/127

6.0/152

6.0/152

7.0/178

32/20632/20648/31060/38770/45281/52364/41364/41380/516

110/710130/839

160/1032

Net Weight (lbs./kg.)

10.5/4.8

11.0/5.0

14.0/6.4

17.5/7.9

17.5/7.9

20.5/9.3

Gross Weight (lbs./kg.)

18.5/8.4

19.0/8.6

22.0/10.0

25.5/11.6

25.5/11.6

28.5/12.9

Min. Supply Air Grille(sq. in./cm.)
Min. Return Air Grille(sq. in./cm.)

Notes:(1)(2)

Supply-Air Grille

Typical Installation ofa Split A/C System

End all model numbers with a ‘115V’ or ‘230V’ depending on the selected voltage.
Add 2.0"/51mm to the height dimension to allow for the duct ring (not included) when theblower is installed in the vertical position.

Flexibleduct

H2Electrical Box

H1Return-Air Grillewith Filter

Display Panel
Condensate
Drain

Condensing Unit
W

Transition Box

DCondensate Drain
Sea-Water Inlet

Sea-Water
OutletSea-Water Pump

Insulated Copper Line Set

Evaporator/Blower
Assembly (Air Handler)

Shut-off Valve

Sea-Water Strainer
Overboard Discharge

Thru-hull Fitting(Clam Shell Scoop)

Emerald TurboVap 12K
unit shown with optionallineset extensions.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
United States & Canada Tech Support
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2696B Rev. 20090904

Environmentally
Responsible

Specificiations and availability subject to change without notice.

Dealer:Direct Expansion Systems

19

CS Series Condensing Units

6K to 16K BTU/hr Capacity Range

CSD12K
condensing
unit shown

Key Benefits
The CS series of condensing units provide heating and cooling■

Models available in 6K, 9K, 12K, and 16K BTU/Hr(60Hz and 50Hz).

■

High-efficiency system with reduced amp draw.

■

Valves and switches provide load balancing andconstant system protection.

■

Symmetrical base for installation flexibility andease of handling.

■

Remote-mountable, moisture-resistant andcorrosion-resistant electrical box.

■

Passport I/O circuit board included in electricalbox of CSD systems.

ensure quiet operation.

■

Factory pre-charged, tested, and leak-checkedprior to shipping.

The electrical box can be mounted remotely. It has a moisture-resistant design■

Meets or exceeds all applicable standards andregulations.

ability in a highly efficient package. The hermetically sealed, high-efficiency
compressor reduces amp draw, while pressure switches, thermal-overload andstart components provide constant system protection and proper operation. In
addition, the expansion device and check-valve assemblies control load balancing
during operation. The system’s copper-encased cupronickel condenser coils arehighly resistant to corrosion that can be caused by continuous seawater flow.
The symmetrical base design provides optimum space efficiency and installation
flexibility for easy handling and positioning of the unit. A built-in hose barb aids incomplete condensate removal from the drain pan. Two sets of vibration isolatorswith a corrosion-resistant enclosure. CS Digital (CSD) units include the Passport I/Ocircuit board.
As with all Marine Air products, quality is assured. Each unit is pre-charged, testrun in all operating modes, and leak-checked at the factory prior to shipping. All
surface components are constructed of or coated with materials resistant tofire and corrosion. Charge Guard® protection provides sealed access ports that
ensure environmental protection and system integrity. All CS condensing units
meet or exceed applicable ABYC and US Coast Guard regulations, CE directives,and general Air Conditioning and Refrigeration Industry (ARI) standards.

ISO 9001:2008
L–2125

Rev. 20080829

20

Direct Expansion Systems

Technical Specifications for 6-16K Condensing Units
Model(1)(2)

CS*6K

CS*9K

CS*12K

Capacity in BTU/hr

6,000

9,000

12,000CS*16K
16,000

Voltage (VAC)(3)115

208-230220-240115

208-230220-240115

208-230220-240115

208-230

Cycle (Hz)/Phase (Ph)(4)

60/1

60/1

50/1

60/1

60/1

50/1

60/1

60/1

50/1

60/1

60/1

220-240
50/1

R-417A Refrigerant (oz/kg)

22/0.622/0.622/0.6

N/A

20/0.6

20/0.6

20/0.6

20/0.624/0.7

N/A

21/0.621/0.6

Full Load Amps (FLA) Cool

7.0

3.7

4.1

6.4

3.2

4.6

8.4

4.4

5.4

12.2

5.7

7.0

Full Load Amps (FLA) Heat

7.7

4.0

4.8

7.2

3.6

5.2

9.2

5.0

6.0

13.5

6.4

8.0

Locked Rotor Amps (Comp)(5)

34.0

20.0

21.2

40.0

20.0

25.6

50.0

31.0

31.0

75.0

36.0

39.0

Kilo-Volt-Amps (KVA) Heat

0.9

0.9

1.2

0.8

0.8

1.2

1.1

1.2

1.4

1.6

1.5

1.9

Max. Circuit Breaker (Amps)

20

10

10

20

10

15

30

15

15

40

20

25

Min. Circuit Ampacity (Amps)

13

8

7

13

7

10

17

10

11

25

12

15

Base Valves (Disch. X Suction)

1/4" X 3/8"

1/4" X 3/8"

1/4" X 3/8"

1/4" X 1/2"

Height (in/mm)(6)15.20/386

15.20/386

15.20/386

15.20/386

Width (in/mm)

13.13/334

13.13/334

13.13/334

13.13/334

Depth (in/mm)

13.13/334

13.13/334

13.13/334

13.13/334

Net Weight (lb/kg)(7)56/25.5

64/29.1

66/30.066/30.0

Gross Weight (lb/kg)(7)63/28.6

74/33.6

75/34.075/34.0

Notes:(1)
BTU and electrical data are based on a 45˚F/7.2˚C evaporator and 100˚F/37.8˚C condenser in cool mode, and a
45˚F/7.2˚C evaporator and 130˚F/54.4˚C condenser in heat mode.
(2)
Add a ‘Z’ or ‘Z50’ after the ‘K’ in the 6K-16K model numbers to denote 208-230V/60Hz or 240-220V/50Hz
respectively.
(3)
Electrical specifications are for reverse cycle units, straight cool units might use smaller circuit breakers.
(4)
Some standard 60Hz units may be operated at 50Hz, at reduced voltages. However, there will be a loss incapacity, and the amp draw may be higher or lower than listed. Dedicated 50Hz units are available that provide
full capacity, but these can not be operated at 60Hz. For more information regarding compressor voltages, referto field notice FN#192-B3 on Dometic Corporation - Environmental Systems’ Customer News & Information
website.
(5)Compressor locked rotor amps (LRA) will vary with voltage and load, and may be higher or lower than listed.
(6)
Electrical box height is 2.6"/66mm; subtract that from unit height if box will be remotely mounted.
(7)
Weights are based on 60Hz/1Ph equipment.
*D = Elite or Passport I/O Control (CSD), M = Mechanical Control (CSM)

Supply Air Grille

Typical Installation ofa Split A/C System

Flexible
ductElectrical Box

Transition Box
Return Air Grillewith Filter

Display panel used with CSD
models. CSM models use a
3-knob mechanical control(see specifications)

Condensate
Drain

Condensing Unit

Condensate Drain
Sea Water Inlet

Sea Water
OutletSea Water Pump

Insulated Copper Line Set
Evaporator/Blower
Assembly

Shut-off Valve

Sea Water Strainer
Overboard Discharge

Thru-hull Fitting(Clam Shell Scoop)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
United States & Canada Tech Support
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2125 Rev. 20080829

Environmentally
Responsible

Specificiations and availability subject to change without notice.

Dealer:Direct Expansion Systems

21

CS Series Multi-Ton Condensing Units

24K to 60K BTU/hr Capacity Range

CSD36R condensing
unit shown

Key Benefits
The CS series of multi-ton condensing units provide heating andcooling ability in a highly efficient package. The hermetically sealed,high-efficiency compressor reduces amp draw, while pressure switches, thermaloverload and start components provide constant system protection and proper
operation. In addition, the expansion device and check-valve assemblies control
load balancing during operation. The system’s copper-encased cupronickel■

Models available in 24K, 30K, 36K, 48K, and 60K
BTU/Hr (60Hz and 50Hz).

■

High-efficiency system with reduced amp draw.

■

Valves and switches provide load balancing andconstant system protection.

■

Symmetrical base for installation flexibility andease of handling.

■

Remote-mountable, moisture-resistant andcorrosion-resistant electrical box.

■

Passport I/O circuit board included in electricalbox of CSD systems.

■

Factory pre-charged, tested, and leak-checkedprior to shipping.

■

Meets or exceeds all applicable standards andregulations

condenser coils are highly resistant to corrosion that can be caused by continuous
seawater flow.
The symmetrical base design provides optimum space efficiency and installation
flexibility for easy handling and positioning of the unit. A built-in hose barb aids incomplete condensate removal from the drain pan. Two sets of vibration isolators
ensure quiet operation.
The electrical box can be mounted remotely. It has a moisture-resistant design
with a corrosion-resistant enclosure. CS Digital (CSD) units include the Passport I/Ocircuit board.
As with all Marine Air products, quality is assured. Each unit is pre-charged, testrun in all operating modes, and leak-checked at the factory prior to shipping. All
surface components are constructed of or coated with materials resistant tofire and corrosion. Charge Guard® protection provides sealed access ports that
ensure environmental protection and system integrity. All CS condensing units
meet or exceed applicable ABYC and US Coast Guard regulations, CE directives,and general Air Conditioning and Refrigeration Industry (ARI) standards.

ISO 9001:2008
L–2126

Rev. 20080829

22

Direct Expansion Systems

Technical Specifications for Multi-Ton Condensing Units
Model (1)(2)

CS*24R

CS*30R

CS*36R

CS*48R

CS*60R

Capacity in BTU/hr

24,00030,00036,00048,00060,000

Voltage (VAC) (3)

208-230 208-230 220-240 380-415 208-230 208-230 220-240 220-240 208-230 208-230 220-240 380-415 208-230 208-230 220-240 380-415 208-230 220-240 440-460

Cycle (Hz)/Phase (Ph) (4)

60/1

60/3

50/1

50/3

60/1

60/3

50/1

50/1

60/1

60/3

50/1

50/3

60/1

60/3

50/1

50/3

60/1

50/1

60/3

R-417A Refrigerant (oz/kg)

46/1.3

N/A

46/1.3

N/A

50/1.4

N/A

N/A

50/1.4

N/A

N/A

56/1.6

N/A

76/2.2

N/A

76/2.2

N/A

80/2.3

N/A

N/A

Full Load Amps (FLA) Cool

7.3

5.4

7.8

3.1

8.4

6.2

9.8

9.8

10.5

6.9

12.0

4.3

13.1

8.2

22.3

5.4

17.2

22.0

6.1

Full Load Amps (FLA) Heat

9.0

6.4

9.9

3.7

10.9

7.4

12.1

11.8

12.9

8.3

14.6

5.0

15.9

9.6

24.8

6.3

22.0

24.8

7.4

Locked Rotor Amps (Comp) (5)

57.0

48.0

55.0

30.0

66.0

48.0

85.1

65.0

73.0

60.0

87.0

35.0

87.0

70.0

132.2

45.0

132.2

138.0

60.0

Kilo-Volt-Amps (KVA) Heat

2.1

2.5

2.4

2.7

2.5

2.9

2.9

2.8

3.0

3.3

3.5

3.6

3.7

3.7

6.0

4.5

5.1

6.0

5.9

Max. Circuit Breaker (Amps)
Min. Circuit Ampacity (Amps)
Base Valves (Disch. X Suct.)

35
22

25
35
15
22
3/8" X 5/8"

10
8

45
26

30
50
17
29
3/8" X 3/4"

40
25

50
29

30
60
18
35
3/8" X 3/4"

15
11

60
35

40
80
23
46
3/8" X 3/4"

30
17

80
46

80
50
5/8" X 3/4"

25
15

Height (in/mm) (6)21.0/546

21.50/546

25.50/648

25.50/648

28.0/732

Width (in/mm)
Depth (in/mm)
Net Weight (lb/kg) (7)16.00/406
16.00/406
115/52.2

16.00/406
16.00/406
127/57.6

16.00/406
16.00/406
135/61.2

16.00/406
16.00/406
145/65.8

24.00/610
24.00/610
173/8.5

Gross Weight (lb/kg) (7)120/54.4

132/59.9

140/63.5

150/68.0

181/81.6

Notes:(1)
BTU and electrical data are based on a 45˚F/7.2˚C evaporator and 100˚F/37.8˚Ccondenser in cool mode, and a 45˚F/7.2˚C evaporator and 130˚F/54.4˚C condenser inheat mode.
(2)
Add a ‘Z’ or ‘Z50’ after the ‘K’ in the 24K-60K model numbers to denote 208-230V/60Hz
or 240-220V/50Hz respectively.
(3)
Electrical specifications are for reverse cycle units, straight cool units might use smaller
circuit breakers.
(4)
Some standard 60Hz units may be operated at 50Hz, at reduced voltages. However,there will be a loss in capacity, and the amp draw may be higher or lower than listed.
Dedicated 50Hz units are available that provide full capacity, but these cannot be
operated at 60Hz. For more information regarding compressor voltages, refer to fieldnotice FN#192-B3 on Dometic Corporation - Environmental Systems’ Customer News& Information website.
(5)Compressor locked rotor amps (LRA) will vary with voltage and load, and may behigher or lower than listed.
(6)
Electrical box height is 3.6”/91mm; subtract that from unit height if box will be remotely
mounted.
(7)
Weights are based on 60Hz/1Ph equipment.
*D = Elite or Passport I/O Control (CSD), M = Mechanical Control (CSM)

Typical Installation ofa Split A/C System

Electrical Box(Remote Mount)

Flexible
duct

Supply Air Grille

Passport I/O display panel usedwith CSD models. CSM models
use a 3-knob mechanicalcontrol (see specifications)

Transition Box

Slave Fan
Speed Control

Electrical Box(Unit Mount)

Condensing
Unit

Return Air Grillewith Filter

Condensate
Drain

Condensate Drain

Sea Water Pump

Sea Water
OutletInsulated Copper Line Set
with Remote Mounted Tee(Do Not Insulate Together)

Evaporator/Blower
Assembly

Shut-off Valve
Sea Water Strainer
Overboard Discharge

Thru-hull Fitting(Clam Shell Scoop)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
United States & Canada Tech Support
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2126 Rev. 20080829

Environmentally
Responsible

Specificiations and availability subject to change without notice.

Dealer:Direct Expansion Systems

23

EBE Series R-410A Evaporators

High-Efficiency Units for Split Air Conditioners

EBE18-230V

Marine Air’s compact EBE split evaporators are draw-through, ductablecooling units with reverse-cycle heating. Featuring a rotatable, high-efficiency

Key Benefits

permanent split capacitor (PSC) blower in which the motor is concealed, EBE series■Compact ductable cooling or heating units.

evaporators are available in capacities from 6K to 36K BTU/hr. EBHE units have electric■

Rotatable, variable speed blower.

heat.

■

Insulated condensate pan with anti-slosh,antifungal foam lining.

■

High-efficiency blower.

■

Environmentally safe R-410A refrigerant.

used. If you are using built-in ductwork, a flexible transition between the blower and■

Air filter included.

duct should be installed.

■“Positive Flow” water displacing
condensate pan.

Vibration-isolation mounting is built into each EBE unit to reduce noise and vibration.

■

Electric heat available on EBHE models.

The PSC blower is supported by a sturdy aluminum bracket with isolation grommets to■

High efficiency evaporator coil.

■

Larger blower inlet for increased air flow
across coil.

■

Blower bracket with vibration isolation
grommets installed.

■

Increased metal thickness on structuralparts for strength.

■

Thermal expansion valve for optimal
performance over a range of conditions.

The EBE Series was designed for installation low in a closet, cabinet, or other enclosed
space, with discharge air ducted to one or more grilles high in the cabin. EBE units canbe used with a combination of plenums and flexible duct, or built-in ductwork may be

reduce possible vibration. The blower’s internal motor housing reduces the overall unit
depth for easier installation and promotes quieter operation.
The drain pan and blower housing are covered with insulating foam which reduces
noise and secondary condensation.
The “positive flow” drain pan has an anti-slosh, antifungal foam lining. Two 1/2 in. (13mm) drains are located on the blower side of the drain pan.
Marine Air DX evaporators can be controlled using the Elite or Passport I/O keypaddisplays on the Passport I/O control system.

ISO 9001:2008
L–2855

Rev. 20110114

24

Direct Expansion Systems

Technical Specifications for EBE Series Evaporators
Capacity(BTU/hr)

Voltage(50/60Hz)

BlowerAmps

Air Flow(cfm/m3h)

EBHE6-1kW-230V

6,000

230

0.98

233/395.91

EBHE8-1kW-230V

8,000

230

0.98

266/451.99

EBHE10-1.5kW-230V

10,000230

0.66

333/565.83

EBHE12-2kW-230V

12,000230

0.56

400/697.68

EBHE16-3kW-230V

16,000230

1.15

533/905.67

Model

Dimensions (in/mm)

Elec. Heat
(kW/Amps)

Height 1(1)Height 2(2)

Width

Depth

Weight(lb/kg)1.0/4.35

11.25/286

12.50/318

13.75/350

12.00/305

14.00/6.35

1.0/4.35

11.25/286

12.50/318

13.75/350

12.00/305

14.00/6.35

1.5/6.52

12.50/318

13.50/343

14.25/362

13.75/349

22.00/9.98

2.0/8.70

12.50/318

13.50/343

14.25/362

14.50/368

23.00/10.43

3.0/13.04

13.50/343

15.50/394

16.00/406

14.75/375

30.00/13.61

With Electric Heat

Without Electric Heat
EBE18-230V

18,000230

1.13

540/917.47

N/A

13.63/346

15.13/384

16.00/406

14.00/356

32.00/14.51

EBE24-230V

24,000230

1.62

800/1359.40

N/A

16.50/419

17.00/432

20.00/508

14.50/368

36.00/16.33

EBE30-230V

30,000230

4.01000/1699.20

N/A

20.50/521

22.00/559

20.75/527

15.00/381

43.00/19.50

EBE36-230V

36,000230

4.01200/2039.00

N/A

20.50/521

22.25/565

20.75/527

17.75/451

42.00/19.05

Notes:(1)(2)

Height from base to top of evaporator coil.
Height from base to top of blower flange.

Interpreting Model Numbers
E

B

H

E

X

XkW

230V

Evaporator

High-Efficiency Blower

Electric Heat

R-410A Refrigerant

x1,000 BTU/hr

Kilowatts of Electric Heat

Voltage

Capacity(BTU/hr.)

Minimum Grille Sizes(sq. in/cm)

Minimum Duct(in/mm)ReturnDischarge

6,000

64/41332/206

4/102

8,000
10,00012,00016,00018,00024,00030,00036,00089/574
100/645130/839
160/1032
200/1290
240/1548
350/2258
360/2323

47/30360/38770/45280/516100/645140/903
170/1097
196/1265

5/127
6/152
6/152
7/178
8/203
8/203
10/254
10/254Height 2
Height 1

Depth

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2855 Rev. 20110114

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Width

Direct Expansion Systems

25

EFD Two-Ton Split Evaporator

With High-Efficiency Blower

Photo courtesy of Cruisers Yachts

Marine Air’s EFD 24,000 BTU/hr. evaporator features a compact,
modular design. For maximum efficiency, the plenum chambers are increased
and the coil has enhanced fins and rifled tubing. This unit also offers easy disassembly

Key Benefits■

Compact modular design with increased
efficiency.

■

Easy disassembly for component access.

■Quiet, efficient blower rotates to vertical or
horizontal positions.

■

Insulated drain pan prevents sweating
and includes two ½ in. (13 mm) FPT drain
hook-ups.

■

Factory pre-charged, tested, and leakchecked prior to shipping.

■

Meets or exceeds all applicable standards
and regulations.

for access to components for maintenance. It works with Marine Air R-22 or R-417A
condensers.
The centrifugal blower is quiet and efficient with a fully-insulated housing. For installation
flexibility, the blower rotates to horizontal or vertical positions. The blower’s internal
motor reduces depth for easier installation. A thermoplastic mounting ring enables easy
installation of ducting or transition box.
The condensate drain pan includes two ½ in. (13 mm) FPT drain hook-ups, and it isinsulated to prevent sweating.
As with all Marine Air products, quality is assured. Each unit is pre-charged, test-run
in all operating modes, and leak-checked at the factory prior to shipping. All surface
components are constructed of or coated with materials resistant to fire and corrosion.
Charge Guard® protection provides sealed access ports that ensure environmental
protection and system integrity. Marine Air evaporators meet or exceed applicable
ABYC and US Coast Guard regulations, CE directives, and general Air Conditioning andRefrigeration Industry (ARI) standards.

ISO 9001:2000
L–2128

Rev. 20110114

26

Direct Expansion Systems

Technical Specifications for E24FDZ/1
Model

Capacity(BTU/hr.)

Voltage @50/60Hz-1Ph

Full Load
Amps (FLA)

Max. Circuit
Breaker (Amps)

Min. Circuit
Ampacity (Amps)

Height 1

E24FDZ/1

24,000

230

0.80

5

1

16.50/419

Dimensions (in/mm)
Height 2
Width
N/A

21.25/540

Depth

Net Weight(lbs/kg)

Gross Weight(lbs/kg)

15.60/396

46.0/21.0

54.0/24.5

Notes:(1)(2)

Height 1 is measured to top of evaporator or blower discharge, whichever is higher.
Height 2 is with blower rotated in field.

Minimum Grille Sizes(sq. in/cm)

Capacity(BTU/hr.)
24,000ReturnDischarge

240/1548

140/903

Minimum Duct(in/mm)
8/203

Discharge

Suction0.38/9.5

0.63/15.9

Flexible
ductElectrical Box

Transition Box
Return Air Grillewith Filter

Display Panel
Condensate
Drain

Condensate Drain
Sea Water Inlet
Sea Water Pump

Sea Water
OutletInsulated Copper Line Set

Evaporator/Blower
Assembly (Air Handler)

Shut-off Valve

Sea Water Strainer
Overboard Discharge

Thru-hull Fitting(Clam Shell Scoop)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2128 Rev. 20110114

Environmentally
Responsible

Specifications and availability subject to change without notice.

Height 2

Width

Supply Air Grille

Typical Installation ofa Split A/C System

Condensing Unit

Height 1

Refrigerant Line Sizes(in/mm)Dealer:Depth

Chilled Water Systems

27

Chiller Compact

Flexibility In Space, Usage & Layout

CHC16RZ

Marine Air’s revolutionary Chiller Compact system is ideal for larger
boats in the 45-70' (15-20 m) range. Available in capacities ranging from 16,000

Key Benefits■

Compact base design allows flexibility in space,
usage and layouts.

■

Individual modules can be multiplexed to provide
precise capacity requirements for any application.

capacity requirements for any application.

■

Thermodynamically matched components assure
maximum performance.

Featuring high efficiency components offering maximum performance, the Chiller■

Rotary and Scroll compressors provide highefficiency performance with less power consumption
and quieter operation. The cylindrical shaped
compressor allows for a compact design.

■

Fewer moving parts ensure higher reliability.

■

Condenser coil is custom fabricated of spiral fluted
cupronickel to provide maximum heat transfer andhigh corrosion resistance.

■

Exclusive Digital Diagnostic Controller (DDC) with
LED display monitors and protects the systemthrough aquastats, high and low pressure switches,
timers, freeze controls and high limit switches.

■

Each unit is evacuated to below 500 microns,
pre-charged, hermetically sealed, load tested andelectronically calibrated at the factory.

■

Charge Guard ® protection provides sealed accessports, ensuring environmental protection and chiller
module integrity.

■

Meet or exceed applicable ABYC and U.S. Coast
Guard regulations, CE Directives and general
Air Conditioning and Refrigeration Industry (ARI)
standards.

to 24,000 BTU/hr, the Chiller Compact uses circulated water in a closed loop in placeof copper refrigerant tubes. The innovative, space-saving compact base of the Chiller
Compact was designed to allow individual modules to be multiplexed to provide precise

Compact uses rotary or scroll compressors which are quieter and consume lesspower. A custom-fabricated condenser coil is constructed of spiral-fluted cupronickel toprovide maximum heat transfer and high corrosion resistance.
The environmentally friendly, hermetically-sealed Chiller Compact units use closedrefrigerant circuits, pre-charged with refrigerant. No additional refrigerant is required
during the installation or at initial start-up and operation of the system.

ISO 9001:2008
L–2135

Rev. 20100409

28

Chilled Water Systems

Technical Specifications for Chiller Compact
Model (1)

CHC16RC(Z, Z50)

CHC20RC(Z, Z50)

CHC24SRC(Z, Z50)

Capacity Cool/RC (BTU/hr)

16,000/17,600

20,000/22,000

24,000/26,400

Advantages of a Marine
Air Chiller System

Voltage (VAC)

115

230

220

230

220

220

230

220

230

220

380

230

220

380

Cycle (Hz)/Phase (Ph)

60/1

60/1

50/1

60/1

50/1

50/1

60/1

50/1

60/3

50/3

50/3

60/1

50/1

50/3

Full Loac Amps (FLA) Cool

8.0

3.8

4.3

5.3

6.1

6.3

6.6

7.5

4.7

4.7

2.7

6.5

7.5

3.1

Full Load Amps (FLA) Heat

11.9

5.6

6.2

7.6

8.4

9.1

8.9

10.4

6.0

7.1

3.5

9.6

10.4

4.1

Locked Rotor Amps (Comp)

67.0

29.0

32.0

45.0

52.0

52.0

54.0

56.0

45.0

56.0

26.0

56.0

56.0

32.0

Kilo-Volt-Amps (KVA)

1.4

1.3

10.4

1.7

1.8

2.0

2.0

2.3

2.4

2.7

2.3

2.2

2.3

2.7

Max. Circuit Breaker (Amps)

35.0

20.0

20.0

25.0

30.0

30.0

35.0

40.0

20.0

25.0

10.0

35.0

40.0

15.0

Min. Circuit Ampacity (Amps)

22.0

12.0

13.0

17.0

17.0

17.0

20.0

23.0

14.0

15.0

8.0

20.0

25.0

9.0

R-407C Refrigerant (oz/g)

10/283

N/A

12/340

N/A

N/A

N/A

13/367

Net Weight 60Hz [50 Hz] (lb/kg)

52/23.6 [58/26.3]

65/29.5 [84/38.1]

84/38.1 [101/45.8]

Gross Weight 60Hz [50 Hz] (lb/kg)

62/28.1 [68/30.8]

75/34.0 [94/42.6]

94/42.6 [111/50.3]

Dimensions

50Hz CHC20 & All CHC24

All CHC16 Units

60Hz CHC20

Height (in/mm)

12.75/324

13.50/343

15.75/400

Width (in/mm)

11.50/292

11.50/292

13.00/330

Depth (in/mm)

18.00/457

18.00/457

18.00/457

CHC Pump Packages (1)PMA1000

P120

P700

Voltage (VAC)

115/230

115/230

115/230(2)(3)

Amps (60Hz/1Ph)

2.1/1.0

4.9/3.5

7.2/3.6

Net Weight (lb/kg)

24/10.9

39/17.7

40/18.1
46/20.9

Gross Weight (lb/kg)

30/13.6

45/20.4

Height (in/mm)

9.0/229 (4)7.5/191

8.0/203

Width (in/mm)

13.0/330

13.0/330

13.0/330

Depth (in/mm)

18.0/457

18.0/457

18.0/457

Notes:(1)Model numbers: CHC = Chiller Compact; 16, 20, 24 = BTU/H x 1000; RC = Reverse Cycle; Z =230/60; Z50 = 220/50; 3 = 3 Phase; S = Scroll compressor (Rotary compressors are used on the
16 & 60Hz 20).
(2)
Add 1.0"/25mm for mounting brackets. Brackets can be mounted on any side of base pan (depth orwidth).
(3)
The 50Hz CHC20s have the same dimensions as the CHC24s.
(4)
The PMA1000 Pump Package is 9.0"/229mm tall at the water outlet and 7.5"/191mm tall at the pump.

■

No refrigeration line sets andmechanical flare fittings which are
subject to leaking refrigerant over
time.

■

Environmentally friendly
hermetically sealed modules.

■

No EPA certified technician required
for startup or field installation.

■

Flexible hose is easier to install andinsulate compared to refrigerant
line sets.

■

Provide full cooling capacity toareas which require fast pull downs
from hot starts.

■

Most applications result in fewer
compressors, which increases
reliability, reduces weight andconserves power.

18/510

Typical Installation of a
Chiller Compact System
Pilot House
Salon

V-BerthGalley/Dining

Ball Valvesat Each Air
Handler In& Out

Guest State
Room

Master State
RoomHeightAll fresh water hoses from chilled water manifolds to chiller
units to be 5/8" white marine grade hose with 3/4" wall
thickness tube insulation. Hoses to have double/reversed
stainless steel hose clamps at each end.

Compact Chiller
Units

Chilled water pump package with pump,
expansion tank, fill water regulating valve,
and water pressure guage.

Depth

Width

Ball valve on chilled water return line
5/8" Marine-grade reinforced seawater inlet/
outlet hoses to have double/reversed stainlesssteel hose clamps at each end.

Seawater Outlet
Seawater Pump

Seawater Strainer
Shut-Off ValveThru-Hull Fitting

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
United States & Canada Tech Support
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2135 Rev. 20100409

Environmentally
Responsible

Specificiations and availability subject to change without notice.

Dealer:M 12
od .5el &s 1
Av 5ai To
la n
bl
e!

Chilled Water Systems

29

MCG Low-Profile R-410A Chillers

Space-Saving Chiller Design

MCG-LP 5-ton
chiller shown

Marine Air MCG Low-Profile Chillers are designed for locations onboard
where height is an obstacle. At 18.25"/464 mm (3 to 6 ton) and 25.2"/640 mm

Key Benefits(12.5 and 15 ton) tall, MCG-LP modules are much shorter than other chillers in the■ Fits into height-restrictive spaces.

same capacity range, but no shorter on high performance and reliability.

■ Reverse cycle standard.

MCG-LP modules provide reverse-cycle cooling and heating and are available in capacities
from 36,000 to 180,000 BTU/hr (3 to 15 tons). Individual modules can be staged for larger
capacities. The R-410A environmentally safe refrigerant has exceptional thermodynamic
properties and maximizes system efficiency.
Performance and reliability is further improved with up to 25 percent more condenser
area than similar low-profile units, and an expansion valve that modulates the refrigerant.

■ Lightweight painted aluminum drain pan(12.5–15 ton only).
■ 3 to 15 ton capacities.
■ Modules can be staged for larger capacities.
■ Up to 25% more condenser area than similar

units.
■ Environmentally safe R-410A refrigerant.
■ Electrical box remotely mounted up to 6'

MCG-LP chillers are monitored and protected by Marine Air’s exclusive Digital
Diagnostic Controller (DDC), which can be installed remotely. For staged systems, theChilled Water Master Controller (CWMC) provides central control over each DDC oneach module in the system. Up to six modules are supported. The CWMC coordinates
all cooling and heating functions, evenly distributes compressor run times, and operates the seawater and circulated water pumps.
The MCG-LP series has stainless-steel drain pans for 3 to 6 ton modules, and lightweight painted aluminum for 12.5 to 15 ton modules. All models have removable PVC
water headers that resist corrosion and erosion.

ISO 9001:2008
L–2735■ Stainless-steel drain pan (3–6 ton only).

Rev. 20100730(1.8 m) away.
■ Removable PVC water headers resist

corrosion and erosion.
■ Expansion valve modulates refrigerant for

improved performance.
■ Hot-gas bypass to provide heating in cold

seawater conditions (3–6 ton only).

30

Chilled Water Systems

Technical Specifications for MCG Low-Profile Chilled Water Series
CW Ø(in/mm)Weight (3)(lbs/kg)

Mounted DDC Dimensions (in/mm) (2)

D2

SW Ø
(in/mm)Height

Width

Depth

24.00/
610

25.38/
645

1.00/
25

1.00/
25

160/7311.00/279

9.80/249

3.70/94

12.69/
322

24.00/
610

25.38/
645

1.00/
25

1.00/
25

160/7311.00/279

9.80/249

3.70/94

12.00/
305

12.69/
322

24.00/
610

25.38/
645

1.00/
25

1.25/
32

174/7911.00/279

9.80/249

3.70/9418.25/
464

12.00/
305

12.69/
322

24.00/
610

25.38/
645

1.00/
25

1.25/
32

174/7911.00/279

9.80/249

3.70/94

245
125
173

25.20/
640

20.13/
511

21.50/
546

36.75/
933

40.03/
1,017

2.00/
51

2.00/
51

335/152

13.30/338

12.00/305

4.30/109

340.0
173.0
196.0

25.20/
640

20.13/
511

21.50/
546

36.75/
933

40.03/
1,017

2.00/
51

2.00/
51

365/166

13.30/338

12.00/305

4.30/109

MCG-LP Single Module Dimensions (in/mm) (2)Model(Capacity)

Volt/Hz/Ph (1)

FLA
Cool

FLA
Heat

LRA

H

W1

W2

D1

MCG-LP 3 Ton(36,000 BTU/hr)

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3

10.9
11.6
7.3
4.0

15.6
16.9
9.4
5.2

112.0
97.0
88.0
44.0

18.25/
464

12.00/
305

12.69/
322

MCG-LP 4 Ton(48,000 BTU/hr)

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3
380-420/50/3

13.0
14.4
9.1
4.7
4.9

19.1
20.7
12.2
6.2
7.0

135.0
136.0
98.0
46.0
51.5

18.25/
464

12.00/305

MCG-LP 5 Ton(60,000 BTU/hr)

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3
380-420/50/3

17.0
21.5
10.6
6.2
6.8

24.7
30.1
14.4
8.2
9.1

158.0
176.0
110.0
75.0
74.0

18.25/
464

MCG-LP 6 Ton(72,000 BTU/hr)

208-240/60/1
208-230/60/3
440-480/60/3
380-420/50/3

23.3
14.2
6.9
9.0

32.5
18.2
9.1
11.7

148.0
149.0
75.0
101.0

MCG-LP 12.5 Ton(150,000 BTU/hr)

208-230/60/3
440-480/60/3
380-420/50/3

29.5
13.8
21.2

38.0
18.0
26.2

MCG-LP 15 Ton(180,000 BTU/hr)

208-230/60/3
440-480/60/3
380-420/50/3

41.9
21.2
25.5

52.0
26.2
31.7

Notes:(1)
For more information regarding compressor voltages, please refer to field notice FNR#192-B3-M.
(2)
All dimensions ± ¼" (6 mm).
(3)
All weights ± 10%.

MCG-LP 3- to 6-Ton Module Dimensions

DDC Box

MCG-LP 12.5- to 15-Ton Module Dimensions

DDC Box

H

H

W1

D1

W1

W2

D2

W2

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2735 Rev. 20100730

Environmentally
Responsible

Specifications and availability subject to change without notice.

D1
D2

Dealer:No
W w
ith Av
R a ila
-4 b
10 le
A

Chilled Water Systems

31

MCG Chiller Series

Modular Chilled Water Air Conditioning

MCG 5-Ton shown

Marine Air’s MCG chilled water series is available in capacities ranging
from 24,000 (2 ton) to 180,000 (15 ton) BTU/hr. Featuring a compact

Key Benefits

base design, MCG modules can be staged to provide a larger system, which is easily■

Small footprint allows installation flexibility.

retrofitted and serviced in the field. Up to six 15-ton stages can be configured for a■

Corrosion-resistant, durable, lightweight
aluminum construction.

■

Can be multiplexed in custom configurations
for large capacities.

■

Remote-mountable electrical box allows easy
access for adjustments or service.

■

Bi-flow expansion valves balance systems
between heat and cool modes.

■

Compact stainless-steel brazed plate heatexchangers for maximum efficiency.

temperatures up to 140°F/60°C.

■

Spiral-fluted cupronickel condenser coilprovides maximum heat transfer.

MCG chillers are monitored and protected by Marine Air’s exclusive Digital Diagnostic■

Exclusive Digital Diagnostic Controller (DDC)
monitors and protects the system.

system total of 1,080,000 BTU/hr., or 90 tons.
Each refrigerant circuit is hermetically sealed and factory pre-charged with R-410A
refrigerant. This environmentally safe refrigerant has exceptional thermodynamic
properties and maximizes system efficiency.
Each condensing unit is monitored and protected with freeze controls, high-limit
switches, high and low aquastats, and timers. These condensing units can be installed
in any convenient location and are unaffected by vibration, moisture or ambient

Controller (DDC), which can be installed remotely. For staged systems, the Chilled
Water Master Controller (CWMC) provides central control over each DDC on each
module in the system. Up to six modules are supported. The CWMC coordinates all■ Environmentally safe R-410A refrigerant.
■

Charge Guard® protection provides sealed
access ports, ensuring environmental
protection and system integrity.

■

All units meet or exceed applicable ABYC
and U.S. Coast Guard regulations, CE
Directives and general Air Conditioning andRefrigeration Industry (ARI) standards.

cooling and heating functions, evenly distributes compressor run times, and operates
the seawater and circulated water pumps.
MCGs are available in single phase or three phase, 50Hz or 60Hz, and all standard
voltages (208, 230, 380, 460 VAC).

ISO 9001:2008
L–2734

Rev. 20100122

32

Chilled Water Systems

Technical Specifications for MCG Modular Chilled Water Series
Model(Capacity)

Volts/Hz/Ph (1)

FLA
Cool

FLA
Heat

LRA

MCG 24(24,000 BTU/hr)

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3

6.4
7.5
5.5
2.7

9.5
11.0
7.3
3.6

MCG 36(36,000 BTU/hr)

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3

10.9
11.6
7.3
4.0

MCG 48(48,000 BTU/hr)

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3
380-420/50/3

MCG 60(60,000 BTU/hr)

MCG Single Module Dimensions (in/mm)(2)

SW
Ø

CW
Ø

Weight(lb/kg)(3)

H1

H2

W1

W2

D1

D2

58.3
67.0
58.0
28.0

17.22/
437

21.74/
552

12.00/
305

12.00/
305

24.00/
610

24.97/
634

1.00" 1.00"

15.6
16.9
9.4
5.2

112.0
97.0
88.0
44.0

23.57/
599

23.57/
599

12.00/
610

12.50/
318

24.00/
610

30.78/
782

1.00" 1.00"

13.0
14.4
9.1
4.7
4.9

19.1
20.7
12.2
6.2
7.0

135.0
136.0
98.0
46.0
51.5

23.57/
599

23.57/
599

12.00/
610

12.50/
318

24.00/
610

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3
380-420/50/3

17.0
21.5
10.6
6.2
6.8

24.7
30.1
14.4
8.2
9.1

158.0
176.0
110.0
75.0
74.0

23.44/
595

26.08/
662

12.00/
610

13.25/337

MCG 72(72,000 BTU/hr)

208-240/60/1
208-230/60/3
440-480/60/3
380-420/50/3

23.3
14.2
6.9
9.0

32.5
18.2
9.1
11.7

148.0
149.0
75.0
101.0

23.44/
595

26.08/
662

12.00/610

MCG 90(90,000 BTU/hr)

208-230/60/3
440-480/60/3
380-420/50/3

19.5
9.8
10.8

24.9
12.4
13.6

195.0
95.0
111.0

27.66/
703

31.07/789

MCG 120(120,000 BTU/hr)

208-230/60/3
440-480/60/3
380-420/50/3

25.3
12.7
13.3

32.8
16.4
17.8

239.0
125.0
118.0

33.61/
854

MCG 150(150,000 BTU/hr)

208-230/60/3
440-480/60/3
380-420/50/3

29.5
13.8
21.2

38.0
18.0
26.2

245
125
173

MCG 180(180,000 BTU/hr)

208-230/60/3
440-480/60/3
380-420/50/3

41.9
21.2
25.5

52.0
26.2
31.7

340.0
173.0
196.0

Height (4)

Width

Depth

194/8811.00/
279

9.80/
249

3.70/
94

194/8811.00/
279

9.80/
249

3.70/
94

30.84/
783

1.00" 1.00" 241/109

11.00/
279

9.80/
249

3.70/
94

24.00/
610

30.07/
764

1.00" 1.25"

263/119

11.00/
279

9.80/
249

3.70/
94

13.25/
337

24.00/
610

30.04/
763

1.00" 1.25"

267/12111.00/
279

9.80/
249

3.70/
94

16.00/
406

17.37/
441

24.00/
610

30.84/
783

1.50" 1.50" 410/186

13.30/
338

12.00/
305

4.30/
109

37.71/
958

16.00/
406

17.40/
442

24.00/
610

30.84/
783

1.50" 1.50" 500/227

13.30/
338

12.00/
305

4.30/
109

46.24/
1174

N/A

18.63/
473

19.50/
495

26.75/
679

31.88/
810

2.00" 2.00" 545/247

N/A

49.20/
1250

N/A

18.63/
473

19.50/
495

26.75/
679

31.88/
810

2.00" 2.00" 600/272

N/A

Dimensions (in/mm) for Multi-Stage Chillers(2)Base Dimensions (in/mm)

No. of
StagesHeight(5)Width(6)2 Stages

1.50/38

28.00/711

DDC Box

DDC Box

CWMC with DDC Dimensions (in/mm)

HeightDepth(6)2- to 6-Ton Modules
31.00/787

24.00/610

Width

Depth

22.00/559

7.75/199

3 Stages(7)1.50/38

41.50/1054

31.00/787

24.00/610

22.00/559

7.75/199

1.50/38

55.50/1410

31.00/787

24.00/610

30.00/762

7.75/199

5 Stages

1.50/38

69.50/1765 31.00/787
24.00/610
7.5- to 10-Ton Modules

35.00/889

7.75/199

2 Stages

3.00/76

36.00/914

35.50/902

24.00/610

22.00/559

7.75/199

3 Stages(7)3.00/76

53.50/1359

35.50/902

24.00/610

22.00/559

7.75/199

4 Stages

3.00/7672.50/1816

35.50/902

24.00/610

30.00/762

7.75/199

5 Stages

3.00/76

88.50/2248 35.50/902
24.00/610
12.5- to 15-Ton Modules

35.00/889

7.75/199

2 Stages

3.00/76

39.25/997

38.75/984

24.00/610

22.00/559

7.75/199

3 Stages(7)3.00/76

59.88/1521

38.75/984

24.00/610

22.00/559

7.75/199

4 Stages

3.00/7680.50/2045

38.75/984

24.00/610

30.00/762

7.75/199

5 Stages

4.00/102101.13/3569

38.75/984

24.00/610

35.00/889

7.75/199

H1

D1
D2

W1
W2
Manifolds

DDC Box

DDC BoxMulti-StageMCG Chiller
Refer to table at left
DDC BoxH
D

W

Notes:(1)
For more information regarding compressor voltages, please refer to field notice FNR#192-B3-M.
(2)
All dimensions ± ¼" (6 mm). (3) All weights ± 10%. (4) Add 1.00" (25 mm) for mounting tabs andminimum clearance on bottom of 4.00" (102 mm) for harness. (5) Add single module height and baseheight for overall height. (6) Manifolds may extend up to 5.00" (127 mm) in front of and up to 7.00"(178 mm) to the side of base. (7) Use 4-stage size for electric heat and 3-4 pumps.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

Single
MCG Module
Refer to table above

H2

4 Stages

L–2734 Rev. 20100122

Mounted DDC Dimensions (in/mm)(2)Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:

DDC BoxChilled Water Systems

33

Staged Chilled Water

Up to Six Stages for Maximum Capacity

SCW 24-Ton

Staged Chilled Water (SCW) chillers are available in capacities ranging
from 48,000 (4 ton) to 1,080,000 (90 ton) BTU/hr. SCWs are available in

Key Benefits■

Cupronickel condenser coils and copper
refrigerant shells for maximum efficiency
and corrosion resistance.

■

Copper-brazed, stainless-steel plateexchangers for maximum efficiency.

limit switches, high and low aquastats, timers and on-board fuses or breakers.

■

Computer matched components provide
maximum cooling/heating capacity.

All access ports to the refrigerant system are protected with Charge Guard®, a factory■

Thermal expansion valves automaticallyadjust to changing load requirements.

■

Individual stages are protected by a circuit
breaker, flow switch, freeze protection,water temperature high limit, high pressurerefrigerant switch, and low pressurerefrigerant switch.

■

Compact base design provides flexibility inengine room layouts.

These condensing units can be installed in any convenient location and are highly■Lightweight aluminum frame construction.

resistant to vibration, moisture or ambient temperatures up to 140°F/60°C. Units meet■

Complete control circuit provides multiple
fail safes for system protection.

■

Vertically mounted units are available.

■

Redundant design assures cooling if one
circuit malfunctions.

■

All compressors accessed from front ofcondensing unit ensuring easy change out.

single phase or three phase, 50Hz or 60Hz, and all standard voltages (208, 230, 380,
460 VAC). Multiple compressors and refrigerant circuits are incorporated to provide
minimal power consumption versus load demands, as well as redundancy throughout
the unit. Each condensing unit is monitored and protected with freeze controls, highinstalled seal, ensuring system integrity from shipping through final installation.
Condenser coils are constructed with cupro-nickel to provide high corrosion resistance.
Unique stainless steel evaporator plates are designed for maximum efficiency of heattransfer. SCWs can be built with circulation pump mounted in the chiller frame. Frames
are welded with marine grade aluminum alloy, primed, then finished with a corrosion
resistant epoxy.

or exceed Coast Guard regulations.

ISO 9001:2008
L–2136

Rev. 20100129

34

Chilled Water Systems

Electrical Specifications for Individual R-410A Stages
Capacity

24,000 BTU/hr.

36,000 BTU/hr.

48,000 BTU/hr

60,000 BTU/hr

72,000 BTU/hr

90,000 BTU/hr

120,000 BTU/hr

150,000 BTU/hr

180,000 BTU/hr

Volts/Hz/Ph(1)208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3
380-420/50/3

208-240/60/1
220-240/50/1
208-230/60/3
440-480/60/3
380-420/50/3

208-240/60/1
208-230/60/3
440-480/60/3
380-420/50/3

208-230/60/3
440-480/60/3
380-420/50/3

208-230/60/3
440-480/60/3
380-420/50/3

208-230/60/3
440-480/60/3
380-420/50/3

208-230/60/3
440-480/60/3
380-420/50/3

FLA Cool

6.4
7.5
5.5
2.7

10.9
11.6
7.3
4.0

13.0
14.4
9.1
4.7
4.9

17.0
21.5
10.6
6.2
6.8

23.3
14.2
6.9
9.0

19.5
9.8
10.8

25.3
12.7
13.3

29.5
13.8
21.2

41.9
21.2
25.5

FLA Heat

10.9
11.6
7.3
4.0

15.6
16.9
9.4
5.2

19.1
20.7
12.2
6.2
7.0

24.7
30.1
14.4
8.2
9.1

32.5
18.2
9.1
11.7

24.9
12.4
13.6

32.8
16.4
17.8

38.0
18.0
26.2

52.0
26.2
31.7

LRA

58.3
67.0
58.0
28.0

112.0
97.0
88.0
44.0

135.0
136.0
98.0
46.0
51.5

158.0
176.0
110.0
75.0
74.0

148.0
149.0
75.0
101.0

195.0
95.0
111.0

239.0
125.0
118.0

245
125
173

340.0
173.0
196.0

Notes:(1)
For more information regarding compressor voltages, please refer to field notice FNR#192-B3-M.
• Due to the number of variables, physical dimensions and weights for SCW Systems are not listed here. Please contact Dometic at 954-973-2477 to discuss your system with a sales representative.

HeatingHeating capabilities can be provided through a variety of choices, depending upon requirements. Reverse-cycle provides the mostefficient heating (four times more efficient than electric heating), but requires a seawater temperature ≥ 40˚F (5˚C). Electric heating
provides adequate capacities for vessels operating in all waters, but is limited by the power (amperage) available for operation. Auxiliary
heating is available through the use of electric heating elements installed in the air handlers. Each of these elements provides 1-3 kW ofheat that can be operated independently or in combination with the central heating circuit to maintain temperatures inside the vessel.
Recommended Heater kW & Stages for Electric Heat (EH) Chillers
Tons Per Stage
2
3
4
5
6
7.5
10
12.5
15

2 Stage
6kW/1 Stage
6kW/1 Stage
10kW/1 Stage
12kW/2 Stage
12kW/2 Stage
20kW/2 Stage
20kW/2 Stage
26kW/2 Stage
30kW/2 Stage

3 Stage
6kW/1 Stage
10kW/1 Stage
12kW/2 Stage
18kW/3 Stage
18kW/3 Stage
26kW/2 Stage
30kW/3 Stage
39kW/3 Stage
45kW/3 Stage

4 Stage
12kW/2 Stage
12kW/2 Stage
18kW/3 Stage
24kW/ 4 Stage
24kW/4 Stage
30kW/3 Stage
40kW/4 Stage
45kW/3 Stage
60kW/4 Stage

5 Stage
12kW/2 Stage
18kW/3 Stage
20kW/2 Stage
18kW/3 Stage
30kW/3 Stage
40kW/4 Stage
52kW/4 Stage
60kW/4 Stage
80kW/4 Stage

Electric Box

C

C

C

C

E

The drip-proof electric box is available with custom harness lengths to fit each application.
A Chilled Water Master Controller (CWMC) Display.

GD

B CWMC circuit board.
C Digital Diagnostic Controller (DDC). Please reference the Chilled Water Master

B

Controller specifications sheet for more details.
D Data plates and wiring diagram.

All compressors, pumps, and heaters are protected by individual circuit breakers E ,controlled by contactors F , and three-phase pumps G are also protected by overloads.
H All wiring from the electric box to the chiller components is connected via feed throughterminals for easy troubleshooting.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2136 Rev. 20100129

Environmentally
Responsible

Specifications and availability subject to change without notice.

A

Dealer:F

D
D

H

Chilled Water Systems

MTS Chillers

For Pleasure Yachts & Commercial Vessels

MTS25 shown

The MTS is a high-capacity modular chiller unit for large
pleasure yachts and commercial vessels. Optional electric

Key Benefits

heaters can provide onboard comfort year round.

■ Modular design for staging multiple

Each module contains a hermetic scroll compressor and shell-and-tube marine-■ Hermetic scroll compressor – avoids

grade condenser, along with other mechanical and electrical components on a single

units.
leaks.

chassis. Multiple modules can be staged as needed to meet the required load.

■ Marine-grade cupronickel shell-and-

These space-saving modules are designed for easy installation in tight spaces. The■ Dual bottom-draining liquid connections

MTS provides easy front access for repair and maintenance of condenser tubes,
heater rods, flow switch, compressor, and replaceable drier cores. Safety measures
include high-pressure switch, refrigerant pressure-relief valve, low-pressure switch,flow switch, high-limit switch, and freeze protection.
A filter drier keeps refrigerant oil clean and dry for long compressor life. With 100 percent pump-down capacity, refrigerant circuit repairs can be made without recovering
the refrigerant.
The MTS 25-ton (279,000 BTU/hr) chiller is available in 380V and 460V models.

ISO 9001:2008
L–2467

Rev. 20080829

tube condenser.
and trap in condenser – optimal
performance in choppy seas.
■ High-pressure switch and pressure-relief valve for safety.
■ Frequency drives – minimize startingamps.
■ Filter drier – keeps refrigerant oil clean

and dry for long compressor life.
■ 100% pump-down capacity – refrigerant

circuit repairs can be made without
recovering the refrigerant.

35

Chilled Water Systems

Technical Specifications for MTS 25-Ton
Model

MTS25 (380V)

MTS25 (460V)

Capacity (BTU/Hr)

279,000

279,000

Voltage

380/60/3

460/60/3

Amps

35.5

35.5

Net Weight (lbs/kg)

1150/429.2

1150/429.2

Height (in/mm)

61.2/1554.48

61.2/1554.48

Width, W1 (in/mm)

19.5/495.3

19.5/495.3

Width, W2 (in/mm)

21.75/552.45

21.75/552.45

Depth, D1 (in/mm)

35.5/901.7

35.5/901.7

Depth, D2 (in/mm)

40.2/1021.08

40.2/1021.08

Clearance, C1 (in/mm)

5/127

5/127

Clearance, C2 (in/mm)

10/254

10/254

Manifolds (see notes)

See notes below

See notes below

Notes:
Allow 8” for manifolds only, or 14” for manifolds with isolation valves. All dimensions +/- 0.5 inch. Clearance
between modules should alternate 5”, 10”, 5”... and at least 5” at each end.

Flowswitch
M
Heater 2(optional)

Manifolds Here

Heater 1(optional)

Clearance

C2

C1

Clearance

36

HeightFilter/Drier
AccessCondenser Tube
AccessFilter/Drier

D1

W1

D2

W2

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2467 Rev. 20080829

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Chilled Water Systems

37

AT Air Handlers for Chilled Water

Improved Design for Better Performance

AT18HV Air Handler

Marine Air’s AT series of air handlers for chilled water systems are drawthough (ducted) units that replace the Flex-Duct and Draw-Through models,

Key Benefits■

Compact design.

■

High-efficiency PSC internal-motor blower
is standard (“HV” models).

standing water, larger drain connections, improved coil design for better cooling■

Improved cooling and dehumidification.

and dehumidifying performance, coil is offset from drain pan edge to ensure all■

Sloped, positive-flow, anti-slosh drain pan
with anti-fungal foam insulation.

dripping condensation, pressure test ports for troubleshooting, and the new 24,000■

Integrated chassis with vibration isolation.

BTU/hr unit uses a high-efficiency, internal-motor blower for quieter operation. On units■

Exposed sheet metal is insulated toprevent secondary condensation.

for access or servicing.

■

Remote air bleeder on 6' (1.8m) of flexible
tubing with ball valve.

Options for “HV” Models:■

User friendly, remote electrical junction
box with 6' (1.9m) wire harness.

■

24K unit with high-efficiency internalmotor blower.

■

Water pressure test ports fortroubleshooting.

■Allowance for connecting variable fan
speed drives.

■

Rotatable blowers.

■

Washable air filter included. Micro-Particle
Anti-Allergenic air filters available.

■

ISTA certified packaging.

and have many improvements and options over the older units.
Significant improvements include: sloped “Positive-Flow” drain pan which reduces

condensation is caught in the pan, redesigned piping so the bypass valve is clear ofwith auxiliary (electric) heat, the new heater design allows removal from the top or side

Electric heat with two-stage electric heat overload (no thermo-fuse), heater assembly
accessible from top or side.
■ Modulating flow control to ensure uniform water distribution.
■ Corrosion resistant coated evaporator coil.
■ Pre-rotated blowers.
■ Right-hand water connections.
■ 3Ph electric heat available.
■

Options for “F” Models:Electric heat with two-stage electric heat overload (no thermo-fuse), heater assembly
accessible from top or side.
■ Low-cost, shaded-pole, external-motor blowers.
■ No-Valve units.
■

ISO 9001:2008
L–2355

Rev. 20091204

38

Chilled Water Systems

Technical Specifications for AT Series Air Handlers
Model (1)

AT4HV

AT6HV

AT9HV

AT12HVAT18HVAT24HVAT36HV

Cooling (BTU/hr / Kcal/hr)

4,000/1,008

6,000/1,512

9,000/2,268

12,000/3,024

18,000/4,536

24,000/6,048

36,000/9,072

Voltage @ 50-60Hz/1Ph

115

230

115

230

115

230

115

230

115

230

115

230

230

Amperage (FLA) Cool

0.8

0.4

1.2

0.6

1.4

0.7

1.4

0.7

2.2

1.0

2.2

1.0

1.6

Optional Electric Heaters(2)

Element Size (kW)

N/A

1.0

1.5

2.0

3.0

3.0

4.0

Heating (BTU/hr / Kcal/hr)

N/A

3,412/860

5,118/1,290

6,824/1,720

10,236/2,579

10,236/2,579

13,648/3,439

Amperage (FLA) Heat

N/A

14.4

18.8

28.3

28.2

10.5

4.9

7.2

9.4

14.0

14.0

19.0

Max. Fuse/in. Circuit Ampacity
Without Electric Heat
With Electric Heat Open

5/2

5/1
N/A

5/3

5/1

5/2

5/1

5/2

5/1

5/3

5/2

5/3

5/2

5/3

10/9

5/5

15/14

10/7

20/18

10/9

30/27

15/14

30/27

15/14

25/20

Water Flow (GPM/LPM)

1.0/3.8

1.5/5.7

2.3/8.5

3.0/11.4

4.5/17.0

6.0/22.7

9.0/34.1

Air Flow (CFM / M3 /Hr) Nominal

130/221229/389278/472338/574465/790506/860

676/1149

External SP (in. H20/eq. Ft.)

0.30/42.3

0.30/42.3

0.30/42.3

0.30/42.3

0.30/42.3

0.30/42.3

0.30/42.3
19.50/495

Height Excluding Blower (in/mm)

10.1/257

10.2/259

11.90/302

12.05/306

14.96/380

16.61/422

Height to Blower (in/mm)

9.5/241

12.63/321

13.25/337

13.88/353

16.50/419

16.68/424

19.50/495

Width (in/mm) (3)14.8/376

15.00/381

16.63/422

18.75/476

20.25/514

22.63/575

26.63/676

Depth (in/mm) (3)8.8/224

12.28/312

12.50/318

12.50/318

12.25/311

15.25/387

18.00/457

Supply Air Duct Diameter (in/mm)

4/102

5/127

6/152

6/152

7/178

8/203

8/203

Return Air Inlet (sq in/sq cm)

64/41370/452

98/632130/839200/1,290

240/1,548

360/2,323

Supply Air Outlet (sq in/sq cm)

32/20635/22649/31670/452

100/645140/903

196/1,265

Remote Mount Electric Box (in/mm)

8.00/203 High X 6.13/156 Wide X 2.00/51 Deep

Drain: 1/2" FPT with PVC HB.
Chilled Water: 1/2" FPT on 4-24K; 1" FPT on 36K with Brass HB on All.

Water Connections
Net Weight (lb/kg) (4)16.0/7.3

18.4/8.3

24.0/10.9

24.0/10.9

32.8/14.9

38.0/17.2

60.0/27.2

Gross Weight (lb/kg) (4)23.0/10.4

28.4/12.9

34.0/15.4

34.0/15.4

36.8/16.7

52.0/23.6

66.0/29.2

Notes:
Model numbers shown are for 115V units. Add a “Z” after the “HV” in the model number to designate
230V (i.e. AT12HVZ). Model number prefixes: -FC = Flow Control; -L# or -R# = Valve and Blower
Rotation (see dwg H3050002); -#kW = Electric Heat Option.
(2)
Auxiliary heating elements are optional, and must be ordered with unit. Add “1KW, 1.5KW, etc.” to themodel number.
(3)
Rotatable feet affect the final dimensions. Front feet add 1.5" to the front, or 1.1" to both sides. Rear feet
do not add to the width or depth when rotated to the side.
(4)
Weights listed are for standard “HV” units. For weights of units with the electric heater option, add
heater elements weights to unit weight. 1.0kW & 1.5kW = 1.5 lbs/0.7 kg; 2.0kW & 3.0kW = 3.0 lbs/1.4
kg. Dimensional weights may apply to shipping charges; contact your sales-admin representative.
(1)

Supply Air Grille
Transition Box(behind)

Supply Air
GrilleRemoteMounted Box

Blower Assembly(vertical position)

HeightExcludingBlower

Flexible Ducting

Heightto Blower
Insulated Reinforced Hose
Dual Condensation
Drain Lines (teed)
Depth

Width
Mounting feet can be rotated;
add 1.1"/28mm to each end.

To Circulation
Circuit

1.50"/38mm(see Note #3)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2355 Rev. 20091204

Service
ValvesEnvironmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Return Air GrilleCondensation lines to Sump

Chilled Water Systems

39

Super Quiet AT-DC Air Handlers

With WhisperCool Technology

AT6DC shown

Dometic creates the new standard in luxury yacht climate control thatyou’ll barely notice – precisely what your clients are asking for – quiet
nights. WhisperCool Technology harnesses engineering refinements to eliminate

Key Benefits■

Advanced super-quiet variable speed
DC fan motor.

■

Operates with Marine Air chilled water air
conditioning systems.

■

Engineering improvements eliminate condensate drain challenges – a positive-flow
drain pan, larger drain connections, offset
coil from drain-pan edge and a redesigned bypass valve.

■

Improved coil design for better dehumidification and cooling.

■

More accessible maintenance points
including water pressure test ports.

■

Rotateable blower.

annoying “motor hum” from traditional air conditioning blowers that occurs at very
low speeds. Incoming alternating current is converted to drive a high-efficiency,
brushless DC fan motor. The result is a much quieter fan operating across a broad
range of variable speeds, permitting the user to select the desired comfort level.
Additional design changes in the air handlers eliminate condensate drain problems,
reduce dripping condensation and standing water issues. An improved coil enhances cooling and dehumidification performance. The redesigned unit also creates easily accessible water-pressure test points for troubleshooting and maintenance.
Better dehumidification, better cooling, less noise… just the kind of performance one
expects aboard a luxury yacht.

ISO 9001:2008
L–2426A

Rev. 20110128

40

Chilled Water Systems

Technical Specifications for AT-DC Air Handlers
Model

AT6DC

AT9DC

AT12DC

AT18DCAT24DCCapacity (BTU/Hr)

6,000

9,000

12,00018,00024,000AT36DC
36,000Volts/Hz/Phase208-230/
50-60/1

208-230/
50-60/1

208-230/
50-60/1

208-230/
50-60/1

208-230/
50-60/1

208-230/
50-60/1
3.9

Amps (FLA) Cool*

1.4

1.4

3.2

3.9

3.9

Optional Heater KW

1.0

1.0

1.5

1.5

3.0

3.0

Heater Amps

4.3

4.3

6.5

6.5

13.0

13.0

Amps (FLA) Heat*

5.7

5.7

9.7

10.4

16.9

16.9

Max Fuse
Without Electric Heat

5.0

5.0

5.0

5.0

5.0

5.0

With Electric Heat

10.0

10.0

15.0

15.0

20.0

20.0

Without Electric Heat

2.0

2.0

4.0

5.0

5.0

5.0

With Electric Heat

7.0

7.0

11.0

12.0

18.0

18.0

GPM/(liters/min)

1.50/5.7

2.25/8.5

3.00/11.4

4.50/17.0

6.00/22.7

9.00/34.1

CFM/(M3/hr)

200/340

280/476

400/680

600/1019

650/1105

670/1130

1.9

0.6

2.3

1.1

0.6

0.5

Height with blower (H1)

13.63/346

13.73/349

13.94/354

16.94/430

16.70/424

19.74/501

Height without blower (H2)

11.08/281

11.79/299

12.05/306

14.83/377

16.70/424

19.74/501

Width (W)14.81/376

16.48/419

18.75/476

20.08/510

22.48/571

26.41/671

Min Circuit Ampacity

External Static Pressure (in H2O)
Dimensions (in/mm)

Depth (D)Duct Ring Diameter (in/mm)

14.27/362

14.55/370

14.49/368

14.83/377

16.42/417

17.15/436

5.00/127.0

6.00/152.4

6.00/152.4

7.00/177.8

8.00/203.2

8.00/203.2

Minimum Supply Air Outlet (sq. in.)

35

49

70

100

140

196

Minimum Return Air Inlet (sq. in.)

70

98

130

200

240

360

two 1/2"
female NPT

two 1/2"
female NPT

two 1/2"
female NPT

two 1/2"
female NPT

two 1/2"
female NPT

two 1/2"
female NPT

1/2"

1/2"

1/2"

1/2"

1/2"

1"

Net Weight (lbs/kg)

23/10.4

27/12.2

29/13.2

39/17.7

44/20.063/28.6

Gross Weight (lbs/kg)

33/15.0

37/16.8

39/17.7

49/22.2

58/26.3

72/32.7

Drain Connections
Chilled Water Connections,Female NPT* Amps listed above are based on maximum speed in free air. Speed would be set well below maximum, and the unit would ordinarily be ducted rather than free air, therefore, the real world amps will
be considerably lower.

W

H1

Service
Pressure
Ports

H2

D

W
1/2" NPT drain

1/2" NPT drain

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2426A Rev. 20110128

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Mounting feet (4)can be rotatedChilled Water Systems

ATL Chilled Water Air Handlers

Designed With Height Constraints In Mind

ATL12DC shown

Marine Air's ATL air handlers are improved low-profile, draw-throughunits for chilled water air conditioning systems. Insulating foam covers the

Key Benefits■

Suspend from above or support frombeneath, vibration isolation included.

foam lining. The ATL series is designed to replace the CHEBC models.

■

Bypass valve has removable power headfor simple servicing.

ATL air handlers are an excellent choice for over-head applications where height■

Valve body is soldered to unit to prevent
leaks.

■The electrical box can be mounted
remotely up to six feet away.

■

Remote air bleeder on six feet (1.8m) of
flexible tubing with easy-operating ballvalve.

■

Optional whisper-quiet DC blowers.

■

Valve on left (standard) or on right(optional).

■

Flow control helps balance chilled water
distribution throughout the boat by
ensuring that no air handler so equipped
receives more flow than required. Thiseliminates the tedious job of trying to
manually balance system flow.

condensate pan, blower housing, shroud, and coil end cover to reduce noise andsecondary condensation. The condensate pan also has an anti-slosh, anti-fungal

is limited. Typically, each cabin or area has one or more air handlers with anindependent climate control to provide passengers with the most comfortableenvironment on the water.
All Marine Air air handlers use corrosion-resistant materials, and are fully insulatedwith deep drain pans to prevent secondary condensation.

ISO 9001:2008
L–2546

Rev. 20110114

41

5
10
2
7
2.25/8.5
300/5100.65/160
8.3/21122.7/577
19.4/493
6/153, 1 ring
49/3161 duct98/632
1/2
Sloped31/14.05
102
7
1.5/5.7
200/340

1.9/470

8.3/21122.7/577
19.4/493
6/153, 1 ring
35/2261 duct70/452

1/2

Sloped31/14.1

Sloped51/23.1

1/2

8.3/21122.7/577
31.4/798
6/153, 2 rings
35/2262 ducts
130/840

1.9/4704
13
3/11
400/680

5
15

12000
208-230/
50-60/1
2.8
2.0
8.7
11.5

ATL12DC

Sloped51/23.1

1/2

8.3/21122.7/577
31.4/798
6/153, 2 rings
49/3162 ducts
200/1290

0.65/160

413
4.5/17600/1020

5
15

18000
208-230/
50-60/1
2.8
2.0
8.7
11.5

ATL18DC

Sloped62/28.1

1/2

10.8/274
19.7/500
43.1/1095
8/204, 1 ring
147/949
1 duct240/1550
Two 1/2" od tube stubs

1.5/370512
6/23
800/1360

5
15

24000
208-230/
50-60/1
3.9
1.5
6.5
10.4

ATL24DC

ATL36DC
36000
208-230/
50-60/1
3.9
1.5
6.5
10.4
15
15
10
12
9/34
1200/2040
0.65/160
10.8/274
21.6/549
62.2/1580
8/204, 1 ring
168/1084
1 duct360/930
1/2
Sloped76/34.5

ATL30DC
30000
208-230/
50-60/1
3.9
1.5
6.5
10.4
15
15
10
12
7.5/281000/1700
1.65/410
10.8/274
21.6/549
62.2/1580
8/204, 1 ring
168/1084
1 duct300/1935
1/2
Sloped76/34.5

Sloped34/15.4

1/2

0.3/752
N/A
4/15
420/710

5
N/A

16000
208-230/
50-60/1
0.9
N/A
N/A
N/A

Sloped34/15.4

1/2

8.10/205
17.60/447
23.40/595
4/102, 2 obrounds
40/2602 ducts
144/930

ATL16F

8.10/205
17.60/447
23.40/595
4/102, 2 obrounds
40/2602 ducts
144/930

0.3/753
N/A
4/15
420/710

5
N/A

2.4
N/A
N/A
N/A

16000
115/60/1

L–2546 Rev. 20110114

Environmentally
Responsible

Specifications and availability subject to change without notice.2009

International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com

(3)

(2)

(1)

Vibration Isolating
Suspension Mounts

Sloped
Pan

H
Drain

D

SlopedDrain Pan

Water Valve and Connections
Behind Valve Cover

Drain

W

Dealer:Blower amps will be reduced at lower speed/cfm static pressure.
The ATL12DC - ATL18DC models are rated at 2.0 kW because the heat is on the blower discharge, and these models have dual blowers. The larger ATL24DC - ATL36DC models require only 1.5 kW because they have a single blower.
Dimensions are ± 0.3" or 8mm.
(4)Units with electric heat have a heater box on the discharge of each blower. Electric heat adds 5.80"/147mm to the depth.
The heater box is only 9.50"/241mm wide (not including electrical gland), and does not add to the height or width of the unit.

Notes:

Amps (FLA) Cool (1)Optional Heater kW (2)Heater Amps
Amps (FLA) Heat (1)Max. Fuse
Without Elec. Heat
With Elec. Heat
Min. Circuit Amps
Without Elec. Heat
With Elec. Heat
Water Flow, GPM/(liters/min)
Air Flow, CFM/(m3/hr)
External Static Pressure(in H2O/Pa)
Dimensions (3)Height (in/mm)
Depth (in/mm) (4)Width (in/mm)
Duct Connections (in/mm)
Min Supply Air Outlet
Per Duct (in2/cm2)
Total Return Air Inlet (in2/cm2)
Drain Connections
Chilled Water Connections,Female NPT (in)Pan Style
Weight (lbs/kg)

Volts/Hz/Phase

9000
208-230/
50-60/1
1.4
1
4.3
5.7

6000
208-230/
50-60/1
1.4
1
4.3
5.7

ATL9DCATL6DC

Model

Capacity (BTU/hr)

Technical Specifications for ATL Air Handlers

1.942Chilled Water Systems

Chilled Water Systems

43

ABL Chilled Water Air Handlers

Low-Profile Models

ABL18DCZ shown

Marine Air's ABL air handlers are improved low-profile, drawthrough units for chilled water air conditioning systems. Insulating

Key Benefits■

DC blowers are strong and quiet atany speed.

■

CBLB models.

Suspend from above or support from beneath,vibration isolation included.

■

Heater elements accessible from underneath(standard) or from above (optional).

ABL air handlers are an excellent choice for over-head applications where height■

Bypass valve has removable power head forsimple servicing.

independent climate control to provide passengers with the most comfortable■

Valve body is soldered to unit to prevent leaks.

environment on the water.

■

The electrical box can be mounted remotely up
to six feet away.

■

Remote air bleeder on six feet (1.8m) of flexible
tubing with easy-operating ball valve.

■

Washable air filter included. Micro-Particle
Anti-Allergenic air filters available.

foam covers the condensate pan, blower housing, shroud, and coil end cover
to reduce noise and secondary condensation. The condensate pan also hasan anti-slosh, anti-fungal foam lining. The ABL series is designed to replace theis limited. Typically, each cabin or area has one or more air handlers with an

Optional Features

ISO 9001:2008
L–2562

Rev. 20090515■

Valve on left (standard) or on right (optional).

■

Heater elements accessible from underneath(standard) or from above (optional).

■

Flow control helps balance chilled water
distribution throughout the boat by ensuringthat no air handler so equipped receives more
flow than required. This eliminates the tedious
job of trying to manually balance system flow.

Chilled Water Systems

Technical Specifications for ABL Air Handlers
Model

ABL18DCZ

Capacity (BTU/Hr)

ABL24DCZ

18,00024,000208-230/50-60/1

208-230/50-60/1

Amps (FLA) Cool

6.4

6.4

Optional Heater KW

3

3Heater Amps

13.04

13.04

Amps (FLA) Heat

19.4

19.4

VoltageMax. Fuse
Without Electric Heat

10

10

With Electric Heat

25

25

Min. Circuit Ampacity
Without Electric Heat

8

8

With Electric Heat

21

21

GPM

4.5

6

CFM

600

800

External static pressure (in H2O)

2.7

2.5

Dimensions (in/mm)
Height Ceiling Mount, H-CM

11.9/302.25

11.9/302.25

Height Floor Mount, H-FM

12.2/309.90

12.2/309.90

Width, W

37.3/947.40

43.3/1099.80

Depth, D

15.8/401.30

15.8/401.30

Dual Duct Rings (in/mm)

6/152.40

6/152.40

Total Return Air Inlet (sq in)
Supply Air Outlet for Each Blower (sq in)

200

240

50 + 50

70 + 70

Drain Connections, Female NPT (in)

1/2"

1/2"

Chilled Water Connections, Female NPT (in)

1/2"

1/2"

Net Weight (lbs/kg)

63/28.35

66/29.94

Gross Weight (lbs/kg)

72/32.40

81/36.74

Notes:
Dimensions are ± 0.3 inches or 7.62 mm. Blower amps will be reduced at lower speed/cfm/static pressure.

Ceiling Mount Vibration Isolators

D

Water Out
Rear
View

H-CM

H-FM

44

Water In (FlowControl Shown)
5.50

Drain
1/2" FPT

Drain
1/2" FPTW

HeaterAccessFloor Mount
Vibration Isolators

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2562 Rev. 20090515

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Chilled Water Systems

ATV Chilled Water Air Handlers

Designed With Depth Constraints In Mind

ATV6DC
model

Marine Air's ATV chilled water air handlers were designed for
applications where very little depth is available. Showcasing a

Key Benefits■

Fits into walls.

■

Unique vertical design.

■

Minimal depth.

■

DC blower provides strong, quiet
performance.

Designed for ducted applications, the ATV has a strong yet quiet DC blower with■

Electric heater included.

internal motor to reduce depth, resulting in easier installation.

■

Capacities from 6K - 36K BTU/hr.

unique vertical layout, this model has the coil low and the blower above.
Put it in the wall. Tall and slim, the ATV makes previously unusable areas
suitable for blower installation. With a depth of only 9.4 in. (240 mm) it can be hidden
in side areas instead of in places above or below, where most air handlers go.

Heat is just a button-press away. Typically, each cabin or living space
has one or more air handlers, each with an independent climate control to provide
passengers with the most comfortable environment on the water. The ATV airhandler includes an electric heater to provide supplemental heat in cold climates. The
ATV can also provide heat to its cabin even while the chiller is supplying cool air toother areas.
Marine Air air handlers have deep drain pans, use corrosion-resistant materials, andare fully insulated to prevent secondary condensation. An optional flow control ishighly recommended to help distribute the flow of chilled water more efficiently.

ISO 9001:2008
L–2564

Rev. 20110107

45

46

Chilled Water Systems

Technical Specifications for ATV Chilled Water Air Handlers
Model

ATV6DCATV9DCATV12DCATV18DCATV24DC

Capacity (BTU/Hr)

6,000

9,000

12,00018,00024,00036,000208-230/50-60/1

208-230/50-60/1

208-230/50-60/1

208-230/50-60/1

208-230/50-60/1

208-230/50-60/1
3.9

Volts/Hz/Ph

ATV36DC

Amps (FLA) Cool

1.4

1.4

3.2

3.9

3.9

Optional Heater KW

1.0

1.0

1.0

1.5

1.5

1.5

Heater Amps

4.3

4.3

4.3

6.5

6.5

6.5

Amps (FLA) Heat

5.7

5.7

7.5

10.4

10.4

10.4

Max. Fuse
Without Electric Heat

5.0

5.0

5.0

5.0

5.0

5.0

With Electric Heat

10.0

10.0

10.0

15.0

15.0

15.0

Water Flow, GPM (liters/min)

2.25/8.5

2.25/8.5

3.00/113.00/116.00/23

9.00/34

Air Flow, CFM (m3/hr)

200/340 (2)280/476

400/680 (2)600/1020 (2)650/1100

750/1275

0.75/186

0.75/186

0.75/186

0.75/186

0.75/186

0.50/12522.3/566

22.3/566

24.1/612

27.8/706

34.4/874

34.4/874

External static pressure (in H2O/Pa)
Dimensions (in/mm)(3)HeightWidth20.2/513

20.2/513

20.2/513

21.2/538

29.3/538

29.3/538

H-B

20.5/521

20.5/521

22.1/561

26.0/660

32.5/826

32.5/826

6.3/160

7.9/201

7.9/201

7.6/193

9.1/2319.1/23111.5/292

11.5/292

D-P

4.3/109

D-V

6.8/173

D-B
Duct Ring Diameter (in/mm)

4.3/1096.8/173

4.3/1096.8/173

7.4/188

9.4/240

9.4/240

10.3/262

5.0/127

6.0/152

6.0/152

7.0/178

8.0/2038.0/203
196/1,265

Minimum Supply Air Outlet (in /cm )35/22649/32070/450100/645140/903

Minimum Return Air Inlet (in2/cm2)

70/452

98/632130/839200/1,290

240/1,548

360/2,323
1/2"

2

2

Drain Connections, Female NPT

1/2"

1/2"

1/2"

1/2"

1/2"

Chilled Water Connections, Female NPT

1/2"

1/2"

1/2"

1/2"

1"

1"

Net Weight (lb/kg)

22/10

25/11

31/14

36/16

65/29

65/29

Gross Weight (lb/kg)

32/15

32/15

40/18

46/21

76/34

76/34

Notes:(1)(2)(3)

Blower amps will be reduced at lower speed/cfm/static pressure.
To avoid water droplets in the airstream, do not exceed this CFM.
Dimensions are ± 0.3 inches or 8mm.

Duct Ring

H-B

W

Height

D-P
D-V
D-B

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2564 Rev. 20110107

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Chilled Water Systems

47

AT-MU Fresh Air Make-Up UnitsFor Use In Fresh Air Make-Up Systems

ATMU 24 shown

Marine Air introduces the new “AT-MU” line of chilled water
fresh air makeup air handlers. These are draw-though (ducted)
units that replace the current models, and offer many improvements
over the existing units.
AT-MU air handlers are designed for use in fresh air make-up (FAMU)
systems where outside air is drawn in by the air handler, cooled,dehumidified, and reheated to room temperature, and then ducted
to various areas in the vessel. The unit consists of a water coil, valve,
electric heater, and a blower mounted on a condensate pan/chassis
with rubber isolation mounting feet.
A specially designed water coil cools and dehumidifies the outside air
in one pass, and is coated, along with the blower and sheet metal, toprevent corrosion. A motorized 3-way bypass valve controls the flowof circulated water through the coil. The high static pressure blower
has a high-efficiency internal motor, and can be rotated as requiredfor installation. An electric heater, with redundant over-temperature
protections, is included to reheat the cooled air up to a comfortabletemperature.
The sloped “Positive-Flow” condensate pan reduces standing water,
and is lined with anti-fungal, anti-slosh foam. An optional modulatingloop-water flow control regulates the water through the unit to ensure
proper water distribution to all air handlers.

ISO 9001:2008
L–2404

Rev. 20080502

Key Benefits
Compact design.
Corrosion resistant coating on evaporator coil,blower, and sheet metal sloped “Positive-Flow”
drain pan with anti-slosh, anti-fungal foam.
■ Vibration isolation mounting feet.
■ Rotatable, high-efficiency internal-motor blower.
■ Integrated 3-way bypass valve with easy-change
power head.
■ Electric heat with two-stage electric heat overload.
■ Heater assembly accessible from top or side.
■ Large coil shroud volume for optimum performance.
■ Washable air filter.
■ Brass hose barbs included for loop water connections.
■ Remote air bleeder on 6ft (1.8m) of flexible tubing
with ball valve.
■ Water pressure test ports for troubleshooting.
■ Modulating flow control ensures proper water
distribution.
■ Hose adapter included for round flex duct connection.
■ ISTA Level IIIA certified packaging.
■■

Options■

Terminal strip style junction box for use with SMX
instead of SCR-based controls. Precise voltage (i.e.,
208 or 230) need not be specified with this option.

48

Chilled Water Systems

Technical Specifications for AT-MU Fresh Air Make-up Air Handlers
Model (1)

AT18HVZ-1.5KW-MU

AT24HVZ-2KW-MU

AT36HVZ-4KW-MU

17,000/4,284

27,000/6,804

53,000/13,356

Capacity (BTU/Hr)/(Kcal/Hr)
Voltage @ 50-60Hz/1Ph

230

230

230

Amperage (FLA)

7.4

9.5

19.1

Max. Fuse/Min. Circuit
Ampacity

10/8

10/10

20/20

(2)

Electric Heaters Size (kW)

1.5

2.0

4.0

Water flow GPM/(liters/min.)4.5/17.0

6.0/22.7

9.0/34.1

CFM/(M3/HR.) NOMINAL

174/296276/469

550/935

External SP (in. H2O/eq. Pa)

0.72/180

0.36/900.75/190

Height15.0/380

16.6/422

19.5/495

Width20.3/514

22.6/575

26.6/676

Depth

12.3/311

15.3/387

18.0/457

Supply Air Duct Ø

5/.0125

6.0/150

8.0/200

100/645140/900

Dimensions (in/mm)(3)Return Air Inlet (sq in/cm)
Loop Water Connections

220/1400

1/2" FPT with 5/8" brass HB

Drain Pan Connections

1" FPT with 1" brass HB

1/2" FPT with PVC 5/8" brass HB

Net Weight (lbs/kg)

34/15.5

41/18.6

63/28.6

Gross Weight (lbs/kg)

38/17.3

55/25.069/31.4

Notes:(1)(2)(3)

Electrical and blower data is based on 50Hz performance.
Verify voltage! Units with SCR-based controls are designed for either 208VAC or 230VAC. Add “208” to the end of the model number for 208VAC units.
Rotatable feet affect the final dimensions. front feet add 1.5” to the front, or 1.1” to both sides. Rear feet do not add to the width or depth when rotated to the side.

Interpreting Model Numbers
AT

12

HV

Z

Size
“AT” Style Air
Handler-FC-2KW

Voltage:
Z = 230High
Efficiency
BlowerVAC (unless
MU208)

KW of ElecHeat
FC = Flow
Control
Blank = No

Width

Depth

24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2404 Rev. 20080502

Environmentally
Responsible

Specifications and availability subject to change without notice.

-L120

Valve & Blower
Orientation
blank = L0
(standard)~1"/25mm(see note 3)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com

208
Voltage: 208
VAC only(2)Fresh Air
Make-upHeightMounting feet can be rotatedto within overall dimensions.

-MU

Dealer:Chilled Water Systems

Fresh Air Make-Up & Extraction Units

Removes Stale Air From the Vessel Interior

T 800 Model shown

A Fresh Air Make Up (FAM) and Extraction systems by Dometic Marine isa must for large displacement yachts, ferries, and commercial vessels.

Key Benefits

The FAM system handles the treatment of incoming air and extraction of stale air to■ Stainless-steel drain pan.

keep the vessel interior full of fresh treated air without fear of overpressure.

■ Fully assembled.

The system normally consists of a treatment unit with a specially designed water coilwhich cools and dehumidifies outside air. If needed, the extraction unit captures andextracts the amount of air specified to be removed, either centrally or distributed.
FAM systems are custom designed and built to the requirements of individual vessels.
There are many configuration options with two major considerations: Structural/material
and treatment/control type. Structural/material options include single walled (standard)or double walled (optional), stainless-steel construction, heavy-duty motors andventilators, to name a few. Treatment/control options include reheat, humidification, full

■ Minimum of 6-row coil.
■ Field serviceable ventilator.
■ Custom designed and built to the client’s

requirements.

Configuration Options■ Single- or double-wall sheet metal.
■ Suspension hardware.
■ Large multi-point discharge plenums.

flow, or balanced flow, and can be controlled by the latest PLC technology or a simple■ Flexible treated water flow options.

on/off switch.

■ Fixed or variable air volume.

FAM units are available in single and 3-phase configurations and are tailored to available
onboard power.

■ Flexible electric reheat combinations.
■ Mist separation and filter types.
■ Ducted or free-flow return.
■ Direct expansion, chilled and hot water

coils.
■ Humidification.
■ Copper fin coils.
■ UV-C germicidal lamps.

ISO 9001:2008
L–2704

Rev. 20090904

49

50

Chilled Water Systems

Technical Specifications for Fresh Air Make Up & Extraction Systems
Model

Air Volume CFM(1)BTU/hr Absorption(2)Average 400/3(3)Dimensions (in/mm)(4)Height

Width

Depth

With Heater(5)T 400

170–260

20,000–27,000

0.39

18.11/460

19.68/500

20.47/520

Width = 28.74/730

T 800

265–400

36,000–52,000

0.39

18.11/460

21.65/550

20.47/520

Width = 30.71/780

T 1000530–700

76,000–98,000

1.43

21.65/550

23.62/600

39.37/1000

Depth = 45.28/1150

T 1400700–880

100,000–120,000

1.94

21.65/550

27.56/700

39.37/1000

Depth = 51.18/1300

T 1700880–1050

120,000–146,000

2.90

27.56/700

27.56/700

43.31/1100

Depth = 55.12/1400

T 26001350–1700

190,000–238,000

4.00

27.56/700

38.19/970

43.31/1100

Depth = 55.12/1400

Notes:
Pulleys provide adjustable air flow. Actual total air flow depends on the size and length of the plenum.
Based on entering water of 45°F/7.2°C.
Based on 400VAC/3-Phase. Actual depends on voltage. Units are available in standard voltages and phase configurations. Note heat amps are not included.
(4)
Dimensions for base chilled water unit includes standard filter only and does not include supply and return plenums, heater, demister or double-walled units.
(5)
Actual dimensions with heater depends on the quantity of heat required.
(1)
(2)
(3)

Extraction Units:
To maintain balanced air pressure that is slightly positive, it is recommended to use an Extractor that will remove slightly less air than has
been added to the vessel by way of the Fresh Air Make Up system. We offer a range of Extraction equipment to suit your needs.

Fresh Air Make Up and Extraction Control Panel:
Vessels are often equipped with multiple Make Up and Extraction units. Each Make Up and Extractor comes with a junction box andcontactor (when required). However, when multiple units are utilized, we will provide a unified control panel to centralize control of thesecomponents.

Make Up and Extraction Options:
As noted on side 1, Fresh Air Make Up and Extraction Systems are completely customized to the client vessel’s requirements. Prior
to utilizing the details found in this specification sheet, please contact your technical sales manager. To improve the turn-around ofyour request, please be prepared to provide the class of the vessel (if applicable), and required air changes. We also need to know if acentral or distributed system is needed. Additionally, we recommend that you over-estimate the amount of room required for the units,
as the dimensions listed above do not include plenums, ducting, or other optional equipment.
Treated water
connections

Fan section

HeightSupply air plenum

Air filter

Wid

Depth

th

Inspection door
Condensate drain Ø 1"

The illustration above shows the Fresh Air Make Up and Extraction
system without the optional heater.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2704 Rev. 20090904

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:No
Vi w Sm u
ar p
Ei p oko rtsnControls

51

Elite Keypad/Display

Ship-Wide Network Capable

Elite keypad/display
with Vimar Eikon bezel

The Elite™ keypad/display is a microprocessor-based controller
designed for the precise monitoring of split and self-contained direct

Key Benefits■

Automatic humidity control — reduces
moisture when the boat is unattended.

application. The control operates at 115 or 230 volts, each operable at 50 or 60 cycles.

■

Cool-only, heat-only, dehumidify, or
automatic mode selection.

The Elite keypad/display has a sleek, modern Euro design. It features a raised buttons■

New optional electric-heat relay.

for easy access and control. The Mode button is used to scroll through the four modes■

Ship-wide network capable.

of operation, simplifying programming. Decorative snap-on Vimar® bezels are available■

Displays Fahrenheit or Celsius.

■

Automatic or three manual fan speeds.

■

Cycle fan with compressor or continuous
fan operation.

■

Cycle pump with compressor orcontinuous pump operation.

■

Compressor time-delay staging for multiple
unit applications.

■Dimmable display lights.

■

Controls shaded pole and split capacitor
fan motors.

■

Compressor fail-safe protection.

adapter adheres to CAN-bus Standard 2.0B■

Programmable de-icing cycle.

and is fully ISO compliant. It is available in two■

Built in air sensor (optional remote sensor).

■

Available with popular Vimar bezel styles(sold separately).

expansion air conditioning systems in marine environments. The control
can also be used with chilled-water air handlers and is called the AH-Elite in thatin a variety of colors and materials to match your vessel’s interior. The original Elite
display, available in grey or white, supports the Vimar Idea line of bezels. A new, second
variety of Elite display is now available in grey only that supports the Vimar Eikon line ofbezels.
The Elite display operates with the
new Passport® I/O circuit board thatutilizes state-of-the-art SMT technology. The
Passport® I/O circuit board has an optional
integrated CAN-bus network adapter thatprovides ship-wide network monitoring ofmultiple DX systems and air handlers. The

ISO 9001:2008
L–2237

Rev. 201000903

52

Controls
high-level CAN-bus communication protocols to support

resistance to external damage or corrosion. A display cable withconnection to several popular helm and cabin touchscreen

modular jacks connects the panel to the system controller. Non-control systems.

volatile memory stores all user-selectable parameters indefinitely

The Elite display is flash programmable, which allows for futureduring operation and through any power-failure situations.

software upgrades without the need to replace the circuit board.

The Elite control meets or exceeds applicable ABYC, U.S. Coast

A ground shield protects against static interference and RF

Guard Regulations and CE Directives.

noise, and the circuit board is conformally coated to provide highTechnical Specifications

Bezel

Voltage (VAC)

115

230

Cycle (Hz)

50/60

50/60

Phase (ø)

11

Elite Control Rear View
Elite Control Front View

Circuits (1)Compressor Output (2)

40A

40A

Locked Rotor Amps (LRA)

80A

80A

R.V. Output (3)¼A¼A

Fan Output

6A

6A

Heater Output

30A

20A

Pump Output (2)

¼ HP

¼ HP

Set Point Temperature Range

65 to 85 / 18 to 29

Display Temperature Range

5 to 150 / -15 to 66

Air Sensor Temperature Range
Sensor Accuracy

Face Plate
Air Sensor

Display Cable with 8-Pin Plug

Electrical Box with
Passport I/O Circuit Board

SPLIT SYSTEMSTo Elite Control

5 to 150 / -15 to 66±2°F at 77°F / ±1.1°C at 25°C

Cables Included (4)Water Inlet Sensor ft./m.

7.00/2.1 cable included with some AH-Elite kits

Other Cables Available (4)Most cables available in 5 ft. (1.5 m.) increments

Display ft./m.

Optional Air Sensor
Cable with 6-Pin Plug

10 - 75/3.0 - 22.9 (typically 15 ft./4.6 m.)

Alternate/Remote Air (optional)

7 - 60/2.1 - 18.3

Outside Air Sensor (optional)

7 - 50/2.1 - 15.2

Pump Sentry (optional)

7 - 60/2.1 - 18.3

Water Inlet Sensor (AH-Elite)

7 - 60/2.1 - 18.3

Return Air
Optional Air Sensor Cardand Connector Mounted
In Return Air Stream

Dimensions
Bezel Type

Optional Air Sensor Mounted
In Return Air Stream

Vimar Idea

Vimar Eikon

Elite Display Dimensions (in/mm)

To Elite Control

Height2.96/75

2.88/73

Width

4.41/112

4.45/113

Depth

1.08/27

1.05/27Height2.19/56

1.88/48Width

3.31/84

2.75/70

Height3.25/83

3.31/84

Width

4.85/123

4.69/119

SELF-CONTAINEDSYSTEMSElectrical Box with
Passport I/O Circuit Board

Panel Cut-Out Dimensions (in/mm)

Bezel Dimensions (in/mm) (5)Return Air

Optional Air Sensor Cable with 6-Pin Plug
Notes:
Maximum loads should not exceed 85% of listed output ratings.
Does not apply to AH-Elite.
Used as water valve output in AH-Elite mode.
(4)
Maximum length for display and air sensor cables is 75 ft. (22.9 m.). Maximum length for water
inlet sensor cable is 75 ft. (22.9 m.).
(5)
Bezels sold separately. Dimensions may vary depending on style.
(1)
(2)
(3)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2237 Rev. 20100903

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:C N
D om ew
es p
ig ac
n! t

Controls

53

Passport I/O Digital Control

For DX & Chilled Water A/C Systems

Passport I/O Compact
digital control shown

The Passport I/O Environmental Control Unit is a microprocessor based
controller, designed for the precise monitoring of direct expansion

Key Benefits■

Automatic humidity control reduces
moisture when the boat is unattended.

■

Cool only, heat only, or automatic mode
selection.

■

Temperature displayed in Fahrenheit or
Celsius.

■Multiple fan speed selections - automaticor six manual speeds.

■

Cycle fan with compressor or continuous
fan operation.

■

Compressor time delay staging for multiple
unit applications.

■

Calibration of fan speed settings andtemperature display to maintain precise
control.

Internal self-diagnostic programs provide complete electronic checks of all lights,■

sensors, keys and circuits. Fused circuits and M.O.V.s (metal oxide varistors) provide

Blank display lights when desired.

■

Controls shaded pole and split capacitor
fan motors.

■

Compressor fail-safe protection.

■

Programmable de-icing cycle.

■

Low voltage for optimum safety.

■

Built-in air sensor (optional remote sensor).

and chilled water air conditioning systems in marine environments. The
control is dual voltage, operating at both 115 and 230 Volts, 50/60 Hz. The display isavailable in both black and white. In chilled water air handlers, the control is referred toas AH-Passport I/O.
The assembly has a ground shield to protect against static interference and RF noise.
The circuit board is conformally coated to provide high resistance to external damage
or corrosion.
A display cable with gold plated phone-type modular jacks connects the panel to thesystem controller. An optional air sensor cable is connected to the circuit board in thesame manner. Non-volatile memory stores all user-selectable parameters indefinitely
during operation or any power failure situations.

component and board protection.
The Passport I/O control meets or exceeds applicable ABYC, U.S. Coast Guard
Regulations and CE Directives.

ISO 9001:2000
L–2630Rev. 20110204

54

Controls

Technical Specifications for Passport
I/O & AH-Passport I/O Environmental
Controls

Key Benefits (continued)■

Universal symbols with tactile switches andembossed power key.

■

Cabin temperature is continuously displayed.

■

Lexan face plate available in black with cameo
graphics.

Voltage (VAC)

115

230

Cycle (Hz)

50/60

50/60

Phase (ø)

1

1■

The circuit board and display cable are factory
installed in the electrical box.

Compressor Output (2)

40A

40A

■

Locked Rotor Amps (LRA)

80A

80A

R.V. Output (3)¼A¼A

Display panels can be mounted with adhesive
strips, or use screws with the optional, soft
bulkhead adapter.

Fan Output

6A

6A

■

Heater Output

30A

20A

Easy connections using phone-type modular jacks
which are shielded and grounded.

Pump Output (2)

¼ HP

½ HP

Circuits (1)Temperature Ranges °F / °C
Set Point Temperature

65 to 85 / 18 to 29

Display Temperature

5 to 150 / -15 to 66

Air Sensor Temperature
Sensor Accuracy
Display Panel Dimensions (in/mm)
Panel Cut-Out Dimensions (in/mm)

Passport I/OControl Rear View

Passport I/O or
AH-Passport I/OControl Front View

5 to 150 / -15 to 66±2°F at 77°F / ±1.1°C at 25°C
3.19"/81mm W X 2.50"/63.5mm H
X 0.94"/23.87mm
2.50"/63.5mm W X 1.875"/47.63mm

Face Plate
Air Sensor

Display Cable with 8-Pin Plug

Cables Included (4)Display ft/m

VCD & VTD: 15/4.6; CMCD: 10/3.0;
CSD: 30/9.1; Chilled Water: 15/4.6

Water Inlet Sensor ft/m

7/2.1 cable included with some AH-Elite
and AH-Passport I/O kits

Other Cables Available (5)Most cables available in 5' increments

Display ft/m

10 - 75/3.0 - 22.9

Alternate/Remote Air (optional)

7 - 60/2.1 - 18.3

Outside Air Sensor (optional)

7 - 50/2.1 - 15.2

Pump Sentry (optional)

7 - 60/2.1 - 18.3

Water Inlet Sensor (AH-Passport I/O)

7 - 60/2.1 - 18.3

Electrical Box with
Passport I/O Circuit Board

SPLIT SYSTEMSTo Passport I/OControl

Optional Air Sensor
Cable with 6-Pin Plug

Notes:

Return Air

Maximum loads should not exceed 85% of listed output ratings.
Does not apply to AH-Passport I/O.
(3)
Used as water valve output in AH-Passport I/O mode.
(4)
Maximum length for display and air sensor cables is 75'. Maximum length for water inlet sensor
cable is 75'.
(1)
(2)

Optional Air Sensor Cardand Connector Mounted
In Return Air Stream
Optional Air Sensor Mounted
In Return Air Stream
To Passport I/OControl

SELF-CONTAINEDSYSTEMSElectrical Box with
Passport I/O Circuit Board

Return Air

Optional Air Sensor Cable with 6-Pin PlugDOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2620 Rev. 20110204

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:

Controls

55

Chilled Water Master Controller

Precise Chiller Monitoring & Coordination

Digital Diagnostic Controller(DDC) Display/Keypad (farright) with PC (not included)

The Chilled Water Master Controller (CWMC) is a microprocessor
based controller designed for the precise monitoring and coordination

Key Benefits■

Provides central control for up to six
chillers.

with the individual DDC* on each chiller. It controls all of the heating and cooling■

Optimizes compressor operation.

functions for each chiller, as well as operation of the seawater and chilled water pumps.

■

LCD display shows status of inlet andoutlet water temperature of each stage,
mixed outlet water temperature of thesystem, compressor run times, anddiagnostic faults.

■

Interfaces with a PC (not included, notrequired) via serial port for remote control
and monitoring. Software is available uponrequest.

■Circuit board is coated for high resistanceto damage or corrosion.

■

Entire assembly is grounded andprotected against static interference andRF noise.

■

Meets or exceeds applicable ABYC,
U.S. Coast Guard Regulations and CE
Directives.

of Digital Diagnostic Controllers (DDC) for multiple chilled water
systems. The control unit provides central control for up to six chillers via interfaces

It optimizes compressor operation by automatically changing the lead compressor toevenly distribute run time.
The two-line lit LCD display provides a scrolling read-out of system status including
inlet and outlet water temperature of each stage, mixed outlet water temperature of
the system, compressor run times, and diagnostic faults including refrigerant high andlow pressure, flow switch, low voltage, freeze warning, and high water temperature
limit. It also interfaces with a PC
via a serial port permitting remotecontrol and monitoring. The PC
software also permits the system
to be programmed in several
different languages. Note that a PC
is optional—not required—and thesoftware is available on request.

*The DDC must be version A23 or greater.

ISO 9001:2008
L–2133

Rev. 20080829(Continued on reverse side)56

Controls
The entire assembly is grounded and protected against staticInternal self-diagnostic programs provide complete

interference and RF noise. The circuit board is conformallyelectronic checks of all lights, sensors, keys, and circuits. The

coated to provide high resistance to external damage or

CWMC controller meets or exceeds applicable ABYC, U.S. Coast

corrosion.

Guard Regulations and CE Directives.

A display cable with phone-type modular jacks connects theChilled Water Master Controller (CWMC)
Typical Installation

display to the circuit board. The circuit board has two display
jacks. One jack is used for the display local to the chiller thesecond jack allows a second display to be remotely installed on
the bridge or elsewhere. Non-volatile memory stores all user-

Display

Optional 2nd Display

selectable parameters indefinitely during operation or any power
CWMC

failure situations.
Fault Indicator Circuit *What is the difference between the
Hydromatic Controller & the CWMC?
Controller Type

CWMC

PC

Serial PortCW Pump orContactor

To Stage Six

HydromaticCompressor Duty Cycling

Yes

Yes

Fahrenheit/Celsius

EitherEitherHigh Pressure Monitoring

Integrated

Integrated

Low Pressure Monitoring

Integrated

Integrated

Flow Switch

Integrated

External

Freeze Protection

Integrated

External

High Limit

Integrated

External

To Stage Five
To Stage FourTo Stage Three

Optional Refrig. Pressure
DDC
Stage
One

DDC
Stage
Two

Optional Refrig. Pressure

Maximum Stages

6

4

Flow Switch

Network Compatible

Yes

No

Freeze Stat

Water Pressure In (System)

Optional

No

Water Pressure Out (System)

Optional

No

Refrigerant Pressure High (Stage)

Optional

No

Refrigerant Pressure Low (Stage)

Optional

No

Hour Meter for Each Stage

Yes

No

Automatic Setpoint Adjustment

Yes(1)

No
No

Optional(4)No

2-Line Backlit LCD,
16 characters/line

Two 3-digit LEDs

Notes:
Whenever a stage is bypassed or off due to a fault, the next stage assumes the setpoint of the
bypassed stage. Subsequent stages are also adjusted.
(2)
Requires computer attached to serial bus. Message codes can be changed in the field fromEnglish to the target language.
(3)
Standard staging delay is adjustable, but when differential is greater than five degrees stages arestarted 15 seconds apart.
(4)
Requires computer and modem interface.
(1)

CW Supply Manifold

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494

L–2133 Rev. 20080829

Chiller Stage 1

CW Return Manifold* Fault indicator circuit not to exceed 250mA, 48VAC/DC (Ref. DWGH1580001).

International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

Mixed CW
OutputTo MCW

Text Display

No

Yes(3)

Freeze Stat
Return Water Temp

To SCW Manifold

Remote Monitoring/Diagnostics

Optional (2)Optional Refrig. Pressure
Flow Switch
Optional Water Pressure In

Hurry Mode

Optional Refrig. Pressure

Optional Water Pressure Out

Multiligual Programming

SW Pump orContactor

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Chiller Stage 2

Controls

57

TWLC for Chilled Water Systems

Advanced Monitoring & Control

Multi-Unit Control
Panel shown

The TWLC (Tempered Water Logic Control) is an advanced
microprocessor chiller control specifically designed for marine
circulated water systems. The TWLC system maximizes system
performance, protects the chillers with advanced fault protection monitoring andshut-down routines, and has easy menu-driven operation supplying the user
with important system information.
System redundancy and easy field repair were the priorities when the TWLC
was developed. Each chiller in a TWLC system has a dedicated power/logic
board, and the boards are networked together to form an integrated system(automatically controlling up to 6 chillers). This design means that a single board
or network failure will not shut down the entire system. The P/L board hasboard-mounted LEDs to help with troubleshooting, replaceable EPROM forsoftware upgrades, and plug-in terminal strips and RJ-12 jacks which allow for
quick field installation.
Interaction with the system is through the TWLC keypad/display. A simple
4-button keypad is used to change operation mode and to navigate through themenus to view and change system parameters. A backlit LCD display supplies
easy to read information about the system, including water temperatures,operation mode, which chillers are running, and other detailed information. Threesmall LEDs on the keypad clearly indicate Cool or Heat modes, and faults. An
alarm buzzer on the keypad can also signal a fault. Additional TWLC keypads
can be installed to allow remote system access.

(Continued on reverse side)

ISO 9001:2008
L–2345

Rev. 20080829

Key Benefits
Up to 6 chiller units can be integrated into one
network.
■ Keypad/Display has a 4-button control and a 4-line
backlit LCD display.
■ Multiple keypad/displays can be used for remote
access.
■ Multi-unit panels come with circuit breakers forcompressor and pump control.
■ Chiller staging based on circulated watertemperature.
■ Compressor rotation to equalize run time of eachunit.
■ Compressor and pump time delay to prevent
simultaneous starting.
■ Records and logs faults and run times.
■ Monitors 12 different faults.
Advanced Options■ Connect to an on-board computer or modem.
■ Current transducers to monitor compressor andpump amperage.
■ Seawater temperature sensors.
■ Refrigerant pressure transducers.
■ Loop water and seawater pressure transducers.
■ Control an optional source of heat (electric
immersion heater or fuel-fired boiler).
■ Remote unit shutdown for load shedding.
■ Fault signal output for remote alarm.
■

58

Controls
Set up and operation of the TWLC is fully automatic. It senses

If a fault is sensed, the fault LED on the TWLC keypad will light

how many units are connected and programs the temperature(and the buzzer will sound, if activated) and the specific fault willstaging and unit rotation of the units to pre-programmed

be displayed on the LCD screen. The fault signal output on theparameters. The TWLC board has non-volatile memory so

P/L boards will also be powered.

settings and recorded information are not lost even if power
is interrupted. The large memory capacity allows the TWLC torecord run time of the compressors and pumps, and store theAnother feature of the TWLC is that it can be connected toan on-board computer or modem to allow full remote accessfault history of each unit.

of the system. Custom software emulates the TWLC on the

The system monitors all the inputs and will display 12 different

to the TWLC keypad/display. If a land phone line is available, afaults based on the information received. Each fault has amodem can be connected and the system can be viewed andspecific routine that protects the unit while helping to prevent

operated remotely, allowing a knowledgeable service agent tonuisance faults. Some will generate a sustained shutdown, which

troubleshoot the system anywhere in the world.

computer screen and navigation through the menus is identicalmust be reset from the TWLC keypad.

Multi-Unit Control Panels
TWLC is available only as part of multi-unit chiller package. The custom panel will include the microprocessor boards, keypad/display, curcuit breakers andrelays for the compressors and pumps. Wiring from the panel to the chillers is also included. A control power transformer is included on 380-460V panels.
Because each multi-unit panel is custom built, there are many options available:• Spare Pump Switch – Selector switches can be added for backup (spare) pumps.
• Multiple Power Inputs – Up to 3 power blocks can be installed to help divide the chiller and pump loads.
• Auxiliary Water Heater – If an auxiliary water heater is desired, the panel can be built with the appropriate breakers and contactors to control the heater.
• Fault Output Relay – A set of “dry” contacts can be installed to operate an alarm on the vessel’s monitoring system.
• Longer Wire Harness – The standard harness is 10 ft (3m) but longer harnesses are available, up to 30' (9m).
• Frame Mounted Panel – If a framed chiller is ordered, the panel can be mounted on the frame.
• Load Shedding – Terminals can be provided in the panel to allow a load-shedding system to remotely shut down individual chillers.
In addition to the options above, two different upgrade packages are available for multi-unit panels:• The Level 1 upgrade package adds current transducers for the compressors and pumps, seawater out temperature sensors in each chiller, a common
seawater inlet temperature sensor, and the computer and modem adapters.
• The Level 2 package includes all items in Level 1, plus: high and low refrigerant pressure transducers for each chiller, a seawater pressure transducer(to install on the discharge of the seawater pump) and a loop water pressure transducer (to install on the inlet of the loop water pump).

TWLC Dimensions
No. of Units
5.1"(130mm)

2-3
4
5

H
H+2"
(+51mm)

5.1"(130mm)W

7.75"(197mm)24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494

L–2345 Rev. 20080829

Height(in/mm
24.0/610
24.0/610
24.0/610

Typical dimensions for standard panels. Options
such as transducers, spare pump switches,
multiple power inputs, etc. might require the next
larger panel size.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com

International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.

Width(in/mm)22.0/560
30.0/760
35.0/890

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:

59

E
W
!

Air Conditioning Accessories

N

In-Duct Breathe Easy™ Air Purifier
Stops Odors & Reduces Unhealthy Contaminants

Customer Comment:“The crew had consistent problems with sore throatsand coughs. So we’ve gone to Dometic. We discovered
the air…went from being almost heavy and saturated
to being a lot lighter. It was easier to breathe…cleaner.
It’s fantastic.”— James Rose-Innes, First Mate, 95 ft. motor yacht
Fort Lauderdale, FL
In-Duct Breathe
Easy Air Purifier

Reduce the odors of tobacco smoke, mildew, mustiness, chemical
vapors and toilets, and inhale fresher, cleaner, healthier air. The in-duct
Breathe Easy Air Purifier uses innovative Photocatalytic Nano-Mesh technology withultraviolet (UV) light to improve air quality. The UV bulb inside uses a specific frequency oflight that produces no harmful ozone.

Key Benefits■ Reduces mold spores, bacteria, viruses,and fumes.
■ Eliminates unpleasant odors.
■ Uses an intense UV light that produces noharmful ozone.

How It Works
Biological contaminants like VOCs, mold spores, bacteria, and viruses pass throughthe air conditioning duct and into the air purifier system.
UV light energy activates the titanium-dioxide catalyst on the surface of the nanomesh structure. The molecules of pollutants and odors that come in contact withthe catalytic nano-mesh structure are reconfigured into non-toxic elements. Vortex
action maximizes air contact with the catalytic surface.
Significantly cleaner, healthier air exits the photocatalytic air purifier.

■ Enhances air quality.
■ Cleaner air may lessen allergy and asthma

symptoms.
■ Silent operation.
■ Up to 100% reduction in diesel fumes,

acetone, benzene, formaldehyde, andother VOCs.
■ Up to 100% reduction in bacteria, fungi,

Non-ozone-producing
UV light bulb

A/C ductmold, and pollen.
A/C duct■ Photocatalytic Nano-Mesh structure issafe and powerful.
■ Photocatalytic Nano-Mesh structure does

not degrade under intense UV light.
■ UV bulb is easy to replace.
■ Tube sizes for common duct diameters.

VOCs, bacteria, fungi,
mold, pollen, and fumes

ISO 9001:2008
L–2701

Rev. 20101022

Photocatalytic NanoMesh structure

Harmless water vapor
and/or carbon dioxide

60

Air Conditioning Accessories

Technical Specifications for In-Duct Breathe Easy Air Purifiers
4" In-Duct
Tube5" In-Duct
Tube

6" In-Duct
Tube7" In-Duct
Tube

Capacity (1)6K BTU/hr

7K - 8K BTU/hr

10K - 12K BTU/hr

14K - 16K BTU/hr

24K BTU/hr

Volts/Hz/mA

115/60/200
220/50/350
230/60/200

115/60/200
220/50/350
230/60/200

115/60/200
220/50/350
230/60/200

115/60/250
220/50/350
230/60/225

115/60/250
220/50/350
230/60/225

UV Bulb Watts

12

12

12

20

20
8.50/216

Model

8" In-DuctTubeØ (in/mm) (2)4.50/114

5.50/140

6.50/165

7.50/191

Height (in/mm) (2)5.25/133

6.50/165

7.50/191

8.50/216

9.50/241

Width (in/mm) (2)10.50/267

10.50/267

10.50/267

13.50/343

13.50/343

H

Ø

W

Notes:(1)(2)

Purification capacity of in-duct units equals or exceeds the airflow and BTU capability of its duct size.
Dimensions are overall, including grommets, insulation, and duct rings.

The Power of Photocatalytic Nano-Mesh Technology

Competitive Advantages
Photocatalytic Nano-Mesh Technology• A 3-dimensional Photocatalytic Nano-Mesh structure coatedwith titanium-dioxide (TiO2) provides maximum surface area
for maximum destruction of airborne contaminants thatcome in contact with it.
• Little or no reduction in air flow because the Photocatalytic
Nano-Mesh structure creates very little static pressure.
• Does not need to be cleaned, maintained, or replaced.

Photocatalytic Nano-Mesh technology removes airborne
contaminants that pass through the system and contact thephotocatalytic surface. As air re-circulates it makes multiple
passes through the system for continuously improving
purification levels.
Photocatalytic air purification only occurs when airborne
contaminants physically touch the catalyst. Innovative
Photocatalytic Nano-Mesh technology creates a much greatercontact surface for much greater results.
The Breathe Easy Air Purifier’s three-dimensional Photocatalytic
Nano-Mesh structure is constructed of metalized foam. This
minutely intricate construction provides 2200% more surface
area for holding the molecular catalytic coating than is possible
with a simple screen structure. This unique design also provides
scant air resistance, so there is no noticeable decrease in air flow.

Dometic’s Photocatalytic
Nano-Mesh structure

Competitor’s screen structure

UV Lamps• Sized for the dimensions of the Photocatalytic Nano-Meshstructure, a single UV bulb with dual tubes provides greater
intensity and service coverage to activate more of thephotocatalytic material for high-performance results.
Safe & Effective Catalyst
Titanium-dioxide is in many common products, including
pigments, processed foods, toothpaste and cosmetics. It isharmless to people, pets, plants, and the environment.
Laboratory Test Results
Testing of the Breathe Easy Air Purifier performed byEnvironmental Diagnostics Laboratory showed up to 98%
reduction in volatile organic compounds (VOCs) and up to
100% reduction in bacteria, fungi, mold, and pollen grains.

In addition, through the science of nanotechnology, the titaniumdioxide catalyst is restructured at the molecular level to havean increased number of contact surfaces. This formation puts
70% larger molecules on the contact surface and dramatically
improves reactivity with contaminants.
Two Innovative Models• In-Duct Tube: Air purifier tube is installed within ducting line anduses the air-conditioning system’s blower to move air past the UV
light and Photocatalytic Nano-Mesh structure. Available in tube
sizes to fit all common duct diameters.
• Portable: Small and lightweight, the portable air purifier canbe situated anywhere and uses an internal fan to move air
past the UV light and Photocatalytic Nano-Mesh structure. It is
suitable for areas up to 100 sq. ft. (9.3 sq. m.) and operates onboth DC and AC voltages.
Note: The Breathe Easy Air Purifier does not fix the source ofongoing odor problems. For example, a leak that caused moldmust be repaired and the mold must be removed.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2701 Rev. 20101022

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:

E
W!

Air Conditioning Accessories

61

N

Portable Breathe Easy™ Air Purifier
Reduces Contaminants & Stops Odors

Customer Comment:
After cleaning up a diesel fuel leak from thegenerator, we still had a persistent petroleum
odor. I installed the portable Breathe Easy Air
Purifier in the galley. A week later all odors werecompletely eliminated.
— John H. Thommen, Guilford, CT

Includes worldwide AC adapter with plugs and
12V DC power plug.

Reduce the odors of tobacco smoke, mildew, mustiness, chemical
vapors, and toilets, and inhale fresher, cleaner, healthier air. Effective inareas up to 100 sq. ft. (9.3 sq. m.), the portable Breathe Easy Air Purifier uses innovative
Photocatalytic Nano-Mesh technology with ultraviolet (UV) light to improve air quality. The
UV bulb inside uses a specific frequency of light that produces no harmful ozone. The unit
operates quietly and has two fan-speed settings.

Key Benefits■ Reduces mold spores, bacteria, viruses,and fumes.
■ Eliminates unpleasant odors.
■ Uses an intense UV light that produces noharmful ozone.

How It Works■ Enhances air quality.

1. Non-ozone-producing UV light reduces biological contaminants like mold spores,
bacteria, and viruses that pass through the air purifier system.

■ Cleaner air may lessen allergy and asthma

2. UV light energy activates the titanium-dioxide catalyst on the surface of the nanomesh structure. The molecules of pollutants and odors that come in contact with thecatalytic nano-mesh structure are reconfigured into non-toxic elements.

■ Quiet operation with two fan speeds.

3. Significantly cleaner, healthier air exits the system.

symptoms.
■ Up to 96% reduction in volatile organic

compounds (VOCs).
■ Up to 99% reduction in bacteria and fungi.
■ Photocatalytic Nano-Mesh structure is

Photocatalytic Nano-Mesh Structure

safe and powerful.
■ Photocatalytic Nano-Mesh structure does

Airborne germs
and odors

not degrade under intense UV light.
■ UV bulb is easy to replace.
■ Effective in areas up to 100 sq. ft.

(9.3 sq. m.).
■ Worldwide AC power adapter with plugs

and 12V DC power plug included.

Harmless water vapor
and carbon dioxide
Non-ozone-producing
UV lampISO 9001:2008
L–2712

Rev. 20100730

62

Air Conditioning Accessories

Technical Specifications for Portable Breathe Easy Air Purifier
Model

Portable

Capacity

Up to 100 sq. ft.
(9.3 sq. m.)

Volts/Hz/mA

115/60/300
220/50/200
230/60/275
12VDC/–/500

UV Bulb Watts

5

Height (in/mm)

1.75/45

Width (in/mm)

6.25/159

Depth (in/mm)

4.50/115
The Power of Photocatalytic Nano-Mesh Technology

Competitive Advantages
Photocatalytic Nano-Mesh Technology• A 3-dimensional Photocatalytic Nano-Mesh structure coatedwith titanium-dioxide (TiO2) provides maximum surface area
for maximum neutralization of airborne contaminants thatcome in contact with it.
• Little or no reduction in air flow because the Photocatalytic
Nano-Mesh structure creates very little static pressure.
• Does not need to be cleaned, maintained, or replaced.

Photocatalytic Nano-Mesh technology removes airborne
contaminants that pass through the system and contact thephotocatalytic surface. As air re-circulates it makes multiple
passes through the system for continuously improving
purification levels.
Photocatalytic air purification only occurs when airborne
contaminants physically touch the catalyst. Innovative
Photocatalytic Nano-Mesh technology creates a much greatercontact surface for much greater results.
The Breathe Easy Air Purifier’s three-dimensional Photocatalytic
Nano-Mesh structure is constructed of metalized foam. This
minutely intricate construction provides 2200% more surface
area for holding the molecular catalytic coating than is possible
with a simple screen structure. This unique design also provides
scant air resistance, so there is no noticeable decrease in air flow.

Dometic’s Photocatalytic
Nano-Mesh structure

Competitor’s screen structure

UV Bulbs

In addition, through the science of nanotechnology, the titaniumdioxide catalyst is restructured at the molecular level to havean increased number of contact surfaces. This formation puts
70% larger molecules on the contact surface and dramatically
improves reactivity with contaminants.
Two Innovative Models• Sized for the dimensions of the Photocatalytic Nano-Meshstructure, a single UV bulb with dual tubes provides greater
intensity and service coverage to activate more of thephotocatalytic material for high-performance results.
Safe & Effective Catalyst
Titanium-dioxide is in many common products, including
pigments, processed foods, toothpaste and cosmetics. It isharmless to people, pets, plants, and the environment.
Laboratory Test Results
Independent testing of the Breathe Easy Air Purifier performed
by Environmental Diagnostics Laboratory showed up to 96%
reduction in volatile organic compounds (VOCs) and up to
99% reduction in bacteria and fungi.

• In-Line Ductable: Air purifier ducting tube is installed within
ducting line and uses the air-conditioning system’s blower
to move air past the UV light and Photocatalytic Nano-Meshstructure. Available in tube sizes to fit all common duct diameters.
• Portable: Small and lightweight, the portable air purifier canbe situated anywhere and uses an internal fan to move air
past the UV light and Photocatalytic Nano-Mesh structure. It is
suitable for areas up to 100 sq. ft. (9.3 sq. m.) and operates onboth DC and AC voltages.
Note: The Breathe Easy Air Purifier does not fix the source ofongoing odor problems. For example, a leak that caused moldmust be repaired and the mold must be removed.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2712 Rev. 20100730

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Air Conditioning Accessories

63

Breathe Easy™ Air Filters

Micro-Particle, Anti-Allergenic Air Filters

Enjoy cleaner, improved air quality on your boat with Breathe Easy™ Air
Filters. Breath Easy micro-particle, anti-allergenic air filters are rated Merv 7, making
them seven times more effective than ordinary air filters.
Breathe Easy Air Filters are efficient and disposable, and are available for most Dometic
air conditioning systems.

Key Benefits■ Rated Merv 7: Seven times more effective

than ordinary foam and slide-in meshscreen air conditioning filters at capturing
airborne micro-particles.
■ Capture diesel smoke, dust, lint, bilge

odors, and pet dander.
■ Electrostatically-charged fibers attract andretain micro-particles in the air.
■ Easy installation for all types and models of

air conditioners.
■ Custom sizes are available.

Breathe Easy™ Air Filters are easily
installed and are available for most
Dometic air conditioning systems.
ISO 9001:2008
L–2698

Rev. 20090807

64

Air Conditioning Accessories
Filter P/N

Fits Cruisair A/C Models

Fits Marine Air A/C Models

Fits Dometic A/C Models

235000600

SXF5, SXF5-1, SHF5, SHF5-1,
ZF5, ZF5-1

VCD5K/1, VCP5K, VCM5K,
VCM5K/1, CLM5KC, CLM5KC/1

235000601

SXF7, SXF7-1, SHF7, SHF71, SXR7-1, SHR7-1, SXR10,
SHR10, SXR12, SHR12235000602

Width x Height
inchesmm

ECM5, ECD5

7-7/8 x 9

200 x 229

VCD7K/1, VCP7K, VCM7K, VCM7K/1, CMCD7K/1, CMCM7K,
CMCM7K/1

ECM6.5, ECD6.5

9-3/8 x 10

238 x 254

SXR7, SHR7 (old style 7K),
ZF3.5

CD3.5, SVCM3.5, CLM3.5

N/A

8-1/8 x 8

206 x 203

235000603

SXF10-1, SHF10-1, ZF10-1

VCD10K/1, VCM10K/1, CLM10KC/1, CMCD10K/1, CMCM10K/1

ECM9, ECD910-7/8 x 10

276 x 254

235000604

SXF10, SHF10, ZF10, ZF12

VCP10K, VCM10K, CLM10KC,
CLM12KC, CMCP10K, CMCM10K

N/A

11-7/8 x 10

302 x 254

235000605

SXF12-1, SHF12-1, SXF161, SHF16-1, ZF12-1, SXR16,
SHR16, ZF16-1, STX14, STX16,
STQ14, STQ16, STH14, STH16

VCD12K/1, VCM12K/1, CLM12KC/1, CMCD12K/1, CMCM12K/1, VCD16K/1, VCM16K/1,
CLM16KC/1, CMCD16K/1,
CMCM16K/1, VTD14, VTD16,
VTM14, VTM16

ECM11, ECD11

10-7/8 x 12

276 x 305

235000606

SXF12, SHF12, SXF16, SHF16,
SXF18, SHF18, ZF16

VCP12K, VCM12K, VCP16K,
VCM16K, VCD18, CLM16KC,
CMCP16K, CMCM16K

ECM15, ECD15

11-7/8 x 12

302 x 305

235000607

SXF24, SXF24-1, SHF24,
SHF24-1 (special order)

VCD24K/1, VCP24K, VCM24K,
VCM24K/1 (special order)

N/A

16-3/8 x 16

416 x 406

235000608

SX24, SH24 (special order)

N/A

N/A

15-1/8 x 17

384 x 432

235000638

STX6, STX8, STQ6, STQ8,
STH6, STH8

VTD6, VTD8, VTM6, VTM8

N/A

8-7/8 x 10-1/4

226 x 261

235000639

STX10, STX12, STQ10, STQ12,
STH10, STH12

VTD10, VTD12, VTM10, VTM12N/A

10-7/8 x 11-1/2

276 x 293

Note to Customer: Please pay close attention to A/C models 10, 12, and 16, and whether or not they have the suffix “-1” or “/1” in the model number. Additionally, unit filters for all 5-16K models with the suffix “-1” and “/1” unit filters are interchangeable with “-2” and “/2” units.

Decide What Size You Need

How To Install the Flter

When To Replace the Filter

Locate the data plate on the air conditioning
unit and determine the model number or
BTU capacity, and measure the size of theevaporator face to determine the correct filter
size. Note: the evaporator is the large squarecorrugated metal piece situated just behindthe blower.

The filter should be installed directly overthe face of the evaporator, using the existingbrackets on the air conditioning unit. If
there are no installed brackets to hold thefilter in place, use the pins contained in thispackage to attach the filter. Press the pins
through the four corners of the filter and into
the spaces between the thin metal fins on
the evaporator face.

Because of its high efficiency in filtering
air, the white filters should be changed at
frequent intervals to maintain the air quality,
and to avoid restricting airflow. Failure tochange filters at the recommended intervals
can cause the air conditioner to shut downfrom lack of air flow or from an icing condition.

Note: These high-efficiency filters should not
be used in conjunction with any other filters or
screens. Make sure you remove any existing
filters or screens in the return air path.

Every 4 months – using the boat 3
weekends of every month.

Width

EVAPORATORHeightPlease contact your Cruisair or Marine Air dealer to order air filter replacements.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2698 Rev. 20090807

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Every 2 months – liveaboard conditions or aboat where the air conditioner runs constantly.

Every 6 months – using the air conditioner
1 – 2 times per month.

E
W!

Air Conditioning Accessories

65

Power Up With SmartStart™

N

Eliminate Startup Spikes

SmartStart™ Model#4220040 shown

The biggest drain on your power source usually occurs when the air
conditioning compressor starts. The big power surge can cause lights and

Key Benefits

other electrical appliances to flicker and falter. In severe cases, the surge can cause the■ Reduces strain on the power source.

boat to lose power completely.

■ Reduces brown-out effects at compressor

The SmartStart is a unique device that smoothes out startup power demand instead■ May enable an inverter to power A/C.

of spiking it, reducing amp requirements by up to 65%. The technology uses dynamic■ May eliminate the need to upgrade yourstart up.

™

feedback control to reduce the inrush of current by starting the compressor motor
slowly. No other soft starter in the industry provides better performance.

generator.
■ Inexpensive.
■ Small and lightweight.

Discover How to Save Money and Energy
Once running, an air conditioning compressor has a much lower, steady amp draw, but
the initial locked-rotor amps needed to start the system can create high current surges

Customer comment:that could adversely affect the operation of an overstrained power source.

“The generator’s control circuit would
trip and stop the generator due tothe inrush of the Emiko’s heat pump.
The SmartStart reduced that inrush
of current so the generator would
continue to run.

In some situations, this gentler method of handling the power surge can mean the difference between keeping the generator you have or investing thousands of dollars in alarger generator.
For boats without a generator, the SmartStart™ may allow the option of powering an air
conditioning system from an inverter.
When running on dock power, a SmartStart™ may resolve issues where the power sourceor connection may be weak.
Continued on reverse side

ISO 9001:2008
L–2700Rev. 20110107

We started with an inrush of 77 amps
and finished with an inrush of only
20 amps. [The SmartStart] is a greatsolution to our problem.”
M/V Emiko, 37 ft. Nordic Tug
Mr. John Poole, Poole Refrigeration Service
Alameda, CA

Air Conditioning Accessories
Little Package

Not only does the SmartStart™ ease strain on the powersource, it’s also less stressful for the compressor itself since

All this power comes in a surprisingly small package. At only

it starts more gently. Additionally, it provides valuable protec-

5 x 3 x 2 in. (127 x 76 x 51 mm), the SmartStart™ takes up little

tion by shutting down the compressor if the power source orspace and weighs only 15 oz. (0.43 kg.). The SmartStart™ isthe connection to the compressor is briefly interrupted, then it

wired directly into the air-conditioning system’s electrical box.

reattempts a soft start after a three-minute delay.

Technical Specifications for SmartStart™
Voltage (volts) /Frequency (Hz)

Model

100

Supported Compressor
Capacity Range (BTUs)

115/60

5K–18K80

4220043

208–240/50–60

12K–30K

704220044

208–240/50–60

36K–60K

60

SmartStart™ Accessories

50

4220045

40

Optional Mounting Tray

Notes:

30• Maximum continuous current for all models: 32 Amps.
• Typical start surge reduction as compared to compressor locked-rotor amperage (LRA): 65%.

20

Up to 65%
Reduction incompressor
startupdemand with
SmartStart™

100
Amps

90

4220040

35
Amps

10
0
Compressor Current
When Starting

SmartStart Wiring Diagram
™

GREEN

WHITE or WHITE/RED

L1

Run
capacitor

Compressor
PROVIDED WIRES & LOOM

RUN

L1

CONTACTOR

BROWN #12

WHITE #12

Control electric box or circuit board
with contactor, relay, or triac thatswitches power to the compressor

RCS

ORANGE or PINKORANGE #16

GND

Make run winding connection
inside electric box with butt
splice provided.

Contactor, relay or triac

BLACK #16

L2/N

TO

L

BLACK or PURPLE

AC Input Power
115-240V/50-60Hz

66

C

COMP
R

NC

L2/N
START

S

RUN
CAP

L2/N

NC

COMMONWIRINGDIAGRAMDOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2700 Rev. 20110107

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Compressor Current
When Starting
With SmartStart™

Air Conditioning Accessories

67

March Marine Pumps

Centrifugal Seawater Pumps for Marine A/C

Clockwise from left:
LC-2CP-MD, AC-5CP-MD,
and LC-3CP-MD

March centrifugal pumps are an excellent choice for providing seawater
circulation for marine air conditioning systems. The proven magnetic drive

Key Benefits

eliminates the troublesome mechanical shaft seal.

■ Magnetic-drive impeller means no seal to

There is no seal wear, power-robbing friction, or leakage through the seal. The impeller■ Efficient motor with low powerand drive magnets are strong, permanent ceramic types, which prevent slippage,ensuring that full motor power is converted into pumping power.

wear, leak, or repair.
consumption.
■ Includes a marine-grade base.
■ 115V and 230V models.

Centrifugal pumps require a flooded inlet and should be mounted below the waterline.
However, an optional priming reservoir is available for applications where the pumpmust be mounted above the waterline (2.0'/0.6 m max.).

■ Liquid-cooled (submersible) and air-cooled motors available.
■ All components in contact with water are

plastic, ceramic, or stainless steel.
“LC” models have liquid-cooled motors and can be run in open air or submerged. “AC”
models have air-cooled, open drip-proof motors and must be in a dry environment.
Replacement parts for March pumps are available through Dometic.

ISO 9001:2008
L–2263

Rev. 20100813■ 6' (1.9 m) power cord standard.
■ Optional priming reservoir available forabove-waterline applications.
■ 1-year warranty on parts.

68

Air Conditioning Accessories

Technical Specifications for March Centrifugal Seawater Pumps
Model

Connections

Max. flow(gpm)

Max. head(ft/m)

Inlet

Outlet5.0

13/3.93/4" MPT

LC-2CP-MD 115V

Motor HP

Volts

Freq.(1)Amps

Weight(lbs/kg)

Motor
type (2)Wet endassembly

1/4" MPT

1/35

115V

50/60Hz

1.00

5.0/2.3

TE/SUB

A-507P

LC-2CP-MD 230V

5.0

13/3.93/4" MPT

1/4" MPT

1/35

230V

50/60Hz

0.53

5.0/2.3

TE/SUB

A-507P

LC-3CP-MD 115V

8.5

19/5.8

3/4" FPT

1/2" MPT

1/20

115V

60Hz

2.00

9.0/4.1

TE/SUB

A-508P

LC-3CP-MD 230V

8.5

19/5.8

3/4" FPT

1/2" MPT

1/20

230V

60HZ

1.00

9.0/4.1

TE/SUB

A-508P

LC-5C-MD 115V

14.5

27/8.2

1" FPT

1/2" MPT

1/8

115V

50/60HZ

2.20

15.5/7.0

TE/SUB

A-506LC

LC-5C-MD 230V

14.5

27/8.2

1" FPT

1/2" MPT

1/8

230V

50/60HZ

1.10

15.5/7.0

TE/SUB

A-506LC

AC-5C-MD 115V

17.0

27/8.2

1" FPT

1/2" MPT

1/8

115V

50/60HZ

2.10

10.0/4.5

OD

A-506

AC-5C-MD 230V

17.0

27/8.2

1" FPT

1/2" MPT

1/8

230V

50/60HZ

1.00

10.0/4.5

OD

A-506

Notes:(1)(2)

Standard 50/60Hz pumps may be operated at 50Hz and reduced voltages. However, there will be a 17% reduction in flow rate and as much as a 30% drop in head in that application. The model LC-3CPMD pump is 60Hz only and may not be operated at 50Hz.
The TE/SUB is a totally-enclosed, liquid-cooled motor and can be operated in the open air or submerged. The OD is an open drip-proof, air-cooled motor and must be kept dry.

Performance Curve

26/7.924/7.322/6.7D

12/3.7
10/3.0

D

-MD
2CP

8/2.4

CP-M

LC-3

14/4.3LC-

Head (feet/meters)

16/4.9

C-M

-MD

-5C

18/5.5-5ACLC

20/6.1

6/1.8
4/1.2
2/0.6
2

4

6

8 10 12 14 16
G.P.M.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2263 Rev. 20100813

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Air Conditioning Accessories

69

Seawater Pumps

Photo courtesy of Cruisers Yachts

Reliable & Heavy-duty Centrifugal Pumps

P711 and PML500CL shown

Marine Air specifies reliable, heavy-duty centrifugal pumps to provide a
steady flow of cooling water through the air conditioning system.

Key Benefits■

High-capacity centrifugal pumps..

The glass-reinforced polypropylene head pumps have magnetic drive impellers, and■Quiet operation.

are available with submersible or air-cooled motors. Larger pumps have bronze heads■

Minimum maintenance.

with mechanical seals, and air-cooled, drip-proof motors. A wide range of pumps and■Single-phase motors have built-in thermal
overload and ignition protection.

motors are available for use in different power environments.
■

Three-phase, ignition-protected motors.

■

Seawater grade construction, with glassfilled polypropylene or bronze pump heads.

■

Submersible or air-cooled motors.

When more than one air conditioning unit is served by a single pump, a separate pump■Vibration isolation mounts standard.

relay is used. To complete the installation, Marine Air can also supply water manifolds,■

High-head pressure models available.

hose, and fittings.

■

Self-priming pumps available.

■

All units meet or exceed applicable ABYC
and U.S. Coast Guard regulations, CE
Directives and general Air Conditioning andRefrigeration (ARI) standards.

Centrifugal pumps must be mounted below the water line. Self-priming pumps are alsoavailable for above-water-line applications. A scoop type through-hull and a seawater
strainer are recommended for proper operation.

ISO 9001:2008
L–2129Rev. 20100813

70

Air Conditioning Accessories

Technical Specifications for Seawater Pumps
1/150

GPM (3) @ Feetof Head (4)2 @ 7'

Capacity
BTU/hr(5)
6,000

1/150

2 @ 7'

6,000

Y

1/35

3 @ 7'

N

1/25

Model

Volts/Hz/Phase

Amps

IP(2)

HP

P800 12VDC
PMLL150-12V DC
PMLL150-24V DC
PML250
PML250C
P900-12V DC
P900-24V DC
PML500L
PML500CL
PML500CKPMA500
PMA500C
PMA500CKPMA1000
PMA1000C
P100
P100Z
P120
P120Z
P700
P700Z
P110Z-3PH
P110-460/3PH
P110-380/3PH

12 VDC
12 VDC
24 VDC
115/60/1
230/50-60/1
12 VDC
24 VDC
115/60/1
230/50-60/1
220/50/1
115/60/1
230/50-60/1
220/50/1
115/60/1
230/50-60/1
115/60/1
230/50-60/1
115/60/1
230/50-60/1
115/60/1
230/50-60/1
230/50-60/3
460/60/3
380/50/3

1.0
1.0
0.5
1.0
0.5
3.8
1.9
2.0
1.0
0.8
2.4
1.2
0.9
2.1
1.0
7.2
3.6
4.9
3.5
7.2
3.6
2.8
1.4
1.7

N
N

P700Z-3PH
P700-460/3PH
P700Z50-3PH
P700-380/3PH

230/50-60/3
460/50-60/3
220/50/3
380/50/3

P710
P710Z
P710Z-3PH
P710-460/3PH
P710Z50
P710Z50-3PH
P710-380/3PH

3/8” FPT X 3/8” OD

Height(in/mm)3.75/95

Width(in/mm)2.81/71

Length(in/mm)5.13/130

Net Weight(lb/kg)1.2/0.5

3/8” FPT X 3/2” HB

3.0/762.75/70

4.5/114

1.0/0.5

12,0003/4" MPT X 1/4" MPT

4.70/1195.60/142

6.20/157

5.0/2.3

3 @ 6.5'

12,0001/2” FPT X 1/2” HB

4.5/114

3.5/899.0/229

4.5/2.0

6 @ 14'6 @ 14'6 @ 9.5'
7.5 @ 14'7.5 @ 14'5 @ 11'

24,00024,00020,00030,00030,00020,0003/4" FPT X 1/2" MPT

5.60/142

5.60/142

7.40/188

9.0/4.1

3/4" FPT X 1/2" MPT

5.0/127

4.0/1029.0/229

7.0/3.2

Inlet X Outlet

Y

1/20

Y

1/12

Y

1/8

12 @ 14'48,000

1" FPT X 1/2" MPT

6.25/159

4.50/114

9.10/231

10/4.5Y

1/3

15 @ 16'

60,0001.25" FPT X 1" FPT

8.50/216

8.50/216

13.9/353

25/11

Y

1/3

21 @ 25'

84,0001.25" FPT X 1" FPT

8.50/216

8.50/216

13.9/353

25/11

Y

1/3

32 @ 21'

128,000

1.25" FPT X 1" FPT

8.50/216

8.50/216

13.9/353

26/12

Y

1/2

18 @ 20'
18 @ 20'
15 @ 15'

72,00072,00060,0001.25" FPT X 1" FPT

8.0/2037.50/191

15.40/391

25/11

2.8
1.4
2.9
1.7

Y

1/2

32 @ 32'
32 @ 32'
32 @ 21'32 @ 21'

128,000

1.25" FPT X 1" FPT

8.0/2037.50/191

15.40/391

30/14

115/50-60/1
230/50-60/1
230/60/3
460/60/3
220/50/1
380/50/3
380/50/3

9.8
4.9
2.2
1.1
7.2
3.3
1.9

N
N
Y
Y
N
Y
Y

1/2
1/2
1/2
1/2
3/4
3/4
3/4

43 @ 32'
43 @ 32'
43 @ 32'
43 @ 32'
43 @ 30'
43 @ 30'
43 @ 30'

172,000

1.50" FPT X 1.50" FPT

9.40/239

7.50/191

15.40/391

34/15

P711
P711Z
P711Z-3PH
P711-460/3PH
P711Z50-3PH
P711-380/3PH

115/50-60/1
230/50-60/1
230/60/3
460/60/3
220/50/3
380/50/3

16.0
8.0
4.2
2.1
4.4
2.5

N
N
Y
Y
Y
Y

1

54 @ 42'54 @ 42'54 @ 42'54 @ 42'54 @ 44'
54 @ 44'

216,000

1.50" FPT X 1.50" FPT

9.40/239

7.50/191

15.40/391

37/17

P711Z 1.5HP
P711Z50 1.5HP

230/60/1
220/50/1

10.0
10.5

N

1.5

60 @ 45'

240,000

1.50" FPT X 1.50" FPT

9.40/239

7.50/191

15.40/391

49/22

Notes:
Electrical and mechanical specifications for 50-60Hz pumps are rated at 60Hz. Operating a 50-60Hz pump at 50Hz
will reduce the pump head by 30% and the GPM by 17%. Do not operate 60Hz only pumps at 50Hz.
Ignition protected.
(3)
GPM flow is rated at indicated pump head.
(4)
Head calculation required for system is dependent on number and size of unit(s), length of hose, use of 90° elbows
and the height of the unit(s) above the pump. Please refer to the Marine Air Systems’ pump sizing guide or consult
the Applications department.
(5)
Capacities given are determined using an average of 3 GPM per ton (12,000 BTU/Hr) at given GPM and head, andare rated for direct expansion (DX) AC systems only.
(1)

Pump

Pump
Discharge

Reversed Double Clamps On
All Hose Connections

(2)

Pump
IntakeBedding Compound
Hull

Contact the applications department for pumps larger than P711.
Seawater Strainer

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2129 Rev. 20100813

Sea Cock
Nut Included With Scoop

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Reinforced Hose

Clam Shell Scoop(Facing Fwd)

Air Conditioning Accessories

71

Pilot House Defroster

With Individual Ducts for Each Pane of GlassPHDCM1.5Z4 shown

The Defroster is designed to remove any moisture or condensationthat may form on the inside of a windshield.

Key Benefits■

Custom configuration for up to six ductring outlets.

■

May be mounted horizontally, vertically,
flat or on edge.

■

Two modes of operation: defrost or fan
only.

■

Constructed of lightweight marine grade
aluminum.

■

Tapered duct housing permits easy
mounting and installation of ducting.

■Slimline style fits easily in overhead
applications or under pilot housecoamings.

■

Two part epoxy polyurethane paint resists
chipping and corrosion.

■

Replaceable filter assembly in back ofmachine.

■Quiet, efficient squirrel cage fan for longservice life.

■

All units meet or exceed applicable ABYC
and U.S. Coast Guard regulations, CE
Directives and general Air Conditioning
and Refrigeration Industry (ARI)
standards.

In order to accommodate the wide range of styles and number of glass areas inyachts, the Defroster incorporates individual ducts dedicated to each pane so that all
surface areas are treated.
This unit will operate in two modes: fan only supplies ambient cabin air to the windshield
for those times when simple ventilation is desired; and fan with thermostaticallycontrolled electric heat that takes cabin air and raises the temperature through the useof finned heating elements mounted in the Defroster chamber.
The unit is typically mounted under the coaming area of the pilot house.

ISO 9001:2008
L–2134

Rev. 20100129

72

Air Conditioning Accessories

Technical Specifications for Defroster
Model

PHDCM1.5

Capacity(1) – Fan (CFM)305

Capacity(1) – Heat (BTU/hr)

5,120

Voltage (VAC)

230

Full Load Amps (FLA) – Fan

0.83

Full Load Amps (FLA) – Heat

6.50

Kilo-Volt-Amps (KVA)

1.69

Max. Circuit Breaker

10.00

Min. Circuit Ampacity

Width

9.00

Width (in/mm)

LengthHeight18.00/457

Height (in/mm)

9.50/241

Length (in/mm)

29.13/714

Net Weight (lb/kg)

23.0/10.4

Ship Weight (lb/kg)

28.0/12.7

Notes:(1)

Ratings at 60Hz. 50Hz operation will be diminished by 17%.

Typical Installation of Defroster

Windshield Diffuser
Flexible Duct

DefrosterElectrical Box

Mounting Platform(Not Included)
Return Air Intake

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2134 Rev. 20100129

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Air Conditioning Accessories

73

Variable Frequency Drive

For Chilled Water A/C Compressors

VFD SQD312

A Variable Frequency Drive (VFD) completely eliminates the large starting inrush current of thecompressor by ramping up voltage and frequency in a controlled time period. This allows running on
limited dockside power, and also protects the generator from overload.
In addition to eliminating inrush, the VFD will also run a 60Hz rated compressor at 60Hz evenwhen input power is 50Hz, which allows full BTU capacity performance (230V only). The drive
also protects the compressor by monitoring input voltage and output current, and will shut down if
a problem is detected. On 208/230V systems, the VFD can “convert” single-phase input power to
3-phase output; however, the VFD current capacity must be derated (see table on second page).
The VFD unit produces a modified sine wave output for smooth acceleration and running, with
precise frequency resolution. It is designed to operate in extreme environments, such as an engine
room. However, the enclosure is ventilated, and must be kept dry. Any direct water contact candamage the unit.
Built-in noise filters are standard and the VFD is CE approved. The Schneider Electric Altivar 312
VFDs incorporate a class A EMC filter into their design. This helps prevent high frequency noisefrom affecting the AC power supply to which the drives are connected. If you have an application
or a power system that requires even lower noise emission, then we recommend you purchase theclass B EMC filters specifically designed to fit with the entire family of Altivar 312 VFDs. To reduce
the harmonic distortion caused by the VFD, we recommend you purchase a line reactor sized
appropriately for the particular VFD.
An LED display allows the user to monitor operation and faults. The VFD is pre-programmed fromthe factory and no further setup is required. Power cables are available through special order.
How to choose the right size Variable Frequency Drive:• Chiller compressor must be 3 phase and each compressor requires a dedicated VFD.
• Multiply the chiller’s reverse cycle amps by 1.10 (10% safety factor).
• Choose the VFD from the Comp Voltage and Max AMP Rating columns (in the table on thefollowing page) depending on compressor voltage and the phase of the input power supply,
respectively.

ISO 9001:2008
L–2413

Rev. 20110422

Key Benefits■

Eliminates compressor start inrush current.

■

208/230V 3 phase output, with 1-phase or
3-phase input.

■

Full 60Hz capacity even at 50Hz input(230V only).

■

Low electronic noise, CE approved.

■

380/480V 3-phase models available.

74

Air Conditioning Accessories

Technical Specifications for Variable Frequency Drives
Model

Reference
NumberComp Voltage

Max AMP Rating
3Ph Input
1Ph Input

HeightDimensions (in/mm)
Width

Depth

Weight(lb/kg)

VFD SQD17.5A230V

4251104

208-230V (1)

17.5

10.1

7.2/184

5.5/140

5.9/150

5.2/2.4

VFD SQD27.5A230V

4251105

208-230V (1)

27.5

15.9

9.1/232

7.1/180

6.7/170

10.4/4.7

VFD SQD33A230V

4251106

208-230V (1)

33.0

19.1

9.1/232

7.1/180

6.7/170

10.4/4.7

VFD SQD54A230V

4251110208-230V (1)

54.0

31.2

13.0/330

9.7/245

7.5/19019.9/9.0

VFD SQD66A230V

4251111208-230V (1)

66.0

38.1

13.0/330

9.7/245

7.5/19019.9/9.0

VFD SQD9.5A460V

4251108

380-460V (2)

9.5

N/A

7.2/184

5.5/14

5.9/150

5.2/2.4

VFD SQD13.4A460V

4251112380-460V (2)

14.3

N/A

9.1/232

7.1/180

6.7/170

10.4/4.7

VFD SQD17A460V

4251202380-460V (2)

17.0

N/A

9.1/232

7.1/180

6.7/170

10.4/4.7

VFD SQD27.7A460V

4251109380-460V (2)

27.7

N/A

13.0/330

9.7/245

7.5/19019.9/9.0

VFD SQD33A460V

4251201

380-460V (2)

33.0

N/A

13.0/330

9.7/245

7.5/19019.9/9.0

Notes:(1)(2)

208-230V VFDs will produce a 60Hz output even with 50Hz input. This allows 60Hz compressors to produce full BTU capacity in 50Hz systems.
High voltage (380-480V) VFDs can be used at 380-420V 50Hz, or 440-480V 60Hz. At these higher voltages the VFD output frequency should by the same as the input.

For programmed VFDs, please call your sales representative with the reference number and programming information (output voltage, input phase, and output frequency).

Height

Width

Depth

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2413 Rev. 20110422

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Air Conditioning Accessories

75

Pump Packages for Chillers

Convenient Solutions for Simpler Installations

P700 Centrifugal
Pump Package

Pump packages reduce the installation time of chilled-water
systems by combining several necessary components in one

Key Benefits■

Convenient packaging of multiple essential
components simplifies installation.

■

Expansion tank protects against thermal
expansion.

■

Bladder-style expansion tank protects
against loss of air cushion.

temperature fluctuations. This relieves pressure that might otherwise result in leaks.

■

Dual-scale pressure gauge is convenientfor US and international customers.

The latest design includes a bladder-style expansion tank. Without the bladder,■

Pressure gauge connected to inlet pipe
gives most accurate reading.

convenient package. The packages include a chilled-water pump, expansiontank, pump drain pan, dual-scale (psi/kPa) pressure gauge, and fill assembly. The fillassembly includes a hose connection, ball valve, and pressure-reducing valve.
The cushion of air in the expansion tank allows the water to expand and contract with

air in the expansion tank would gradually dissolve into the water and be bled off.
Eventually, the protective cushion of air would be gone.
The pressure gauge is connected to an inlet pipe on the pump for the most accurate
reading of system return water pressure.

ISO 9001:2008
L–2541

Rev. 20100409

76

Air Conditioning Accessories

Technical Specifications for Pump Packages
Model

PMA1000

PMA1000CPMA1000CK

P120

Voltage (V/Hz/Phase)

115/60/1

230/60/1

240/50/1

115/60/1

230/50/1

P120Z
230/60/1

115/60/1

P700

230/50/1

P700Z
230/60/1

Amps (FLA)

2.1

1.0

1.1

4.9

3.5

3.5

7.2

3.6

3.6

Recommended Applications: Total
Air Handler Capacity (BTU/hr)

16-23

16-23

16

24-48

17-23

24-48

49-12024-84

49-120Height (in/mm)

9.2/233

9.2/233

9.2/233

9.2/233

9.5/241

9.5/241

9.5/241

9.5/241

9.5/241

Pan Width, W1 (in/mm)

11.7/297

11.7/297

11.7/297

11.7/297

15.4/391

15.4/391

15.4/391

15.4/391

15.4/391

Overall Width, W2 (in/mm)

12.9/327

12.9/327

12.9/327

12.9/327

17.1/434

17.1/434

17.1/434

17.1/434

17.1/434

Depth, D (in/mm)

18/457

18/457

18/457

18/457

18/457

18/457

18/457

18/457

18/457Chilled Water “in” connections,
female NPT

1" female1" female1" female1.25" female

1.25" female

1.25" female

1.25" female

1.25" female

1.25" female

Chilled Water “out” connections,NPT

1/2" male

1/2" male

1/2" male1" female1" female1" female1" female1" female1" female

Net Weight, (lbs/kg)

33/14

33/14

33/14

48/21

48/21

48/21

49/22

49/22

49/22

Gross Weight, (lbs/kg)

47/21

47/21

47/21

62/28

62/28

62/28

62/28

62/28

62/28

Notes:• Dimensions are ± 0.125 inches.
Safety note:• Pump packages do NOT include backflow preventers. If the chilled-water fill assembly might be supplied by a potable water supply, then a reduced pressure zone (RPZ) backflow preventer should beinstalled between the fill assembly and the potable water supply to prevent contamination of the potable water.

Expansion Tank
Ball Valve &Fill Connection
Pump Electric Box

Gauge

H

H

W1

D

W1

W2

D

W2

PMA1000

P120/P700

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2541 Rev. 20100409

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Air Conditioning Accessories

77

Discharge & Return Air Grilles

Aluminum, Wood, & Plastic Styles

Assorted aluminum, wood, andplastic grilles shown

Marine Air discharge and return air grilles are available in a wide
assortment of dimensions, styles, and materials to blend with any yacht’s
interior.
The vanes of discharge grilles are secured in nylon bushings for easy dependable
positioning. RA-type return air grilles have one row of fixed vanes. Wood return air grilles
have a lint screen which can be removed for cleaning.
Round plastic discharge grilles are also offered in several colors with and without shut-

Key Benefits■

Large selection and variety of grilles■

Standard and custom materials complement
all yacht interiors.

■

Custom sizes available for any application.

Wood Frame Grilles■

Pop out louver panels with return air grilles
have easy-to-clean replaceable filters.

■

Supply air grilles have double-deflection,
moveable louvers available in anodized
bronze or aluminum finish.

off dampers.
Micro-Particle Anti-Allergenic air filters, designed to capture diesel smoke, dust, lint,bilge odors, and pet dander, are available for Marine Air A/C systems. These filters
mount to the unit’s evaporator coil and are eight times more efficient than standard
filters. Due to the high efficiency of these new filters, they should be inspected andreplaced at frequent intervals. When using a filter on the unit, do not also have a filter on
the grille, as that would cause too much restriction of the airflow.

ISO 9001:2008
L–2130Rev. 20080829

Aluminum Grilles■

Supply air grilles have adjustable louvers to
direct air flow.

■

Return air grilles feature durable fixed-vanelouvers.

■

Return air grilles are supplied with orwithout filters depending on system
requirements.

■

Painted grilles are sprayed withpolyurethane.

■

Multiple color selection.

78

Air Conditioning Accessories

Grille Dimensions

Grille Sizing Per Unit
Unit Capacity
in BTU/hr

ReturnSupplySq. In.

Sq. cm

Sq. In.

Sq. cm

4,000

64

412.9

32

206.5

5,000

64

412.9

32

206.5

6,000

70

451.6

35

225.8

7,000

80

516.2

45

290.3

9,000

98

632.3

49

316.1

10,000

100

645.2

60

387.1

12,000

130

838.8

70

451.6

16,000160

1032.380

516.2

18,0002001290.4100

645.2

24,0002401548.5140

903.3

30,000350

2258.2

170

1096.836,0003602322.7196

1264.648,0004803097.02561651.7

Notes:• Supply and Return Air Grille minimums are required to achieve rated capacity.
• Custom sizes and custom painted grilles are available. Contact Marine Air Systems for pricing and availability.

Product Characteristics
Wood Frame Grilles• Cut-out dimensions are the nominal grille size, i.e., a 10" X 5" VH requires a 10" X 5"
(25.4cm X 12.7cm) cut out.
• Outside frame dimensions are 0.9375" ± 0.0625" (2.4cm ± 0.16cm) lager than nominal
grille size, i.e., a 10" X 5" VH has overall dimensions or 10.9375" X 5.9375" (27.8cm X
15.1cm).
• Depth of grilles: VH is 1.375" (3.5cm), VML is 1.875" (4.8cm), RA is 0.875" (2.2cm),
measured from back of frame.
• Frame (flange) dimensions are 0.563" (1.4cm) on all sides.
Aluminum Grilles• Cut-out dimensions for the TH, TV, and TRA style grilles are 0.375" (1.0cm) smaller than
the nominal grille size, i.e., a 10" X 5" TH requires a 9.625" X 4.625" (24.4cm X 11.7cm)
cut-out. The TRAF style grilles are 0.125" (0.3cm) smaller.
• Outside frame dimensions are 0.875" (2.2cm) larger than the nominal grille size, i.e., a
10" X 5" TH has overall dimensions of 10.875" X 5.875" (27.6cm x 14.9cm).
• Depth of grilles: TH and TRA are 0.875" (2.2cm), TRAF is 1" (2.5cm), measured fromback of frame.
• Frame (flange) dimension is 0.625" (1.6cm) on all sides.

Wood Frame Grilles
Supply Air,
Supply Air,Primary
Secondary Closeable
Model VH
Model VML
7" X 7"
4" X 4"
10" X 5"
6" X 4"
12" X 5"
8" X 4"
8" X 8"
14" X 4"
14" X 5"
10" X 4"
14" X 6"
12" X 4"
16" X 4"
Supply Air,
Return Air
Secondarywith Filter
Model VH
Model RA4" X 4"
7" X 7"
12" X 14"
14" X 7"
6" X 4"
8" X 8"
14" X 10"
8" X 4"
8" X 10"
10" X 4"
11" X 8"
14" X 12"
12" X 4"
12" X 12"
16" X 9"
Plastic Grilles(Round and Closeable Supply Air Grilles)
Model
2SA
3SA
4SA
Duct Size2"
3"
4"
Aluminum Grilles
Supply Air
Return Air
Model TRAF (with Filter);Model TH
Model TV
Model TRA
(without Filter)
4" X 4"
10" X 4"
8" X 11"
14" X 7"
7" X 7"
12" X 3"
10" X 4"
14" X 10"
8" X 4"
12" X 4"
11" X 7"
14" X 12"
10" X 4"
12" X 5"
11" X 8"
16" X 9"
10" X 5"
12" X 6"
11" X 12"
20" X 5"
14" X 4"
12" X 12"
22" X 7"
14" X 5"
28" X 6"
14" X 6"
14" X 7"
16" X 4"
18" X 3"
20" X 5"
24" X 3"Note:
• Multiply the dimensions above by 2.54 to calculate for centimeters.

Plastic Grilles (Circular)• Depth of grilles: 2SA is 1.31" (3.3cm), 3SA is 2.16" (5.5cm), 4SA is 2.38" (6.0cm),
measured from back of frame.
• Frame (flange) dimensions: 2SA is 2.75" (7.0cm), 3SA is 3.875" (9.8cm), 4SA is 5.50"(14.0cm), in diameter.
• Cut-out dimensions are 2.0" (5.1cm), 3.0" (7.6cm), and 4.0" (10.2cm) respectively, indiameter.
• A special adapter is available to use the 4SA with 3.0" (7.6cm) ducting.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2130 Rev. 20080829

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Air Conditioning Accessories

79

Ducting & Transition Boxes

A Full Range of Diameters & Lengths Available

Vacuum formed and aluminumtransition boxes, and ducting shown

Specifications

Key Benefits

Vacuum-Formed Transitions:

Ducting Design• Opening dimensions are 0.375" (0.95cm) larger than transition size (i.e., 10" X 5"
VF has a 10.375" X 5.375" opening. 25.4cm X 12.7cm VF has a 26.4cm X 13.7cm
opening).
• Flange to flange dimensions are 1.5" (3.8cm) larger than transition size (i.e., 10"
X 5" VF = 11.5" X 6.5" flange to flange. 25.4cm X 12.7cm VF = 29.2cm X 16.5cm
flange to flange).
• Depth of 4x VF models is 4.0" (10.2cm) (measured from back of flange).
• Depth of 5x and 6x VF models i.e., either 4.5" (11.4cm) or 5.75" (14.6cm)
depending on use of round or obround rings.
• Flange dimensions are 0.5625" (1.43cm) on all sides.
Square Vacuum-Formed Transitions:• Available in 5.25" and 6.25" (13.34cm and 15.88cm) square vacuum-formed
transition boxes.
• Opening dimensions are 0.5" (1.27cm) larger than transition size.
• Flange to flange dimensions are 1.75" (4.4cm) larger than transition size.
• Depth is 0.125" (0.32cm) longer than the transition size.
• Flange dimensions are 0.625" (1.59cm) on all sides.
Vacuum Formed T-Boxes:• Height of 10,000, 12,000 and 16,000 T-box with mounting flange is 7.875" (20.0cm).
• Height of 7,000 T-box with mounting flange is 6.875" (17.5cm).
• The 10,000, 12,000 and 16,000 T-boxes accommodate 6", 5" and 4" duct rings on
one side and 5", 4" and 3" duct rings on the other side (15.2cm, 12.7cm, 10.2cm
and 12.7cm, 10.2cm, 7.6cm respectively).
(Continued on reverse side)

ISO 9001:2008
L–2131

Rev. 20080829■

Two types of ducting available: round/wirewith woven fabric and round/wire and mylar
fabric shell with 1.0" (2.6cm) wall thickness
insulation.

■

Full range of diameters and lengths.

■

All ducting attaches easily to associatedrings.

Transition Box Design■

Large selection and variety available inaluminum and ABS plastic.

■

Air flow designed and tested components.

■

Matched to Marine Air Systems’ grilles andblowers.

■

Non-restrictive air flow.

■

All rings designed for close tolerance fit withducting.

■

Perimeter flanges on all boxes for mounting
ease.

■

Aluminum Style Transitions and Boxes are
fully insulated, available in standard andcustom sizes, and are ideal for applications
where space is limited.
(Continued on reverse side)80

Air Conditioning Accessories• The 7,000 T-box accommodates 5" and 4" duct rings on one side and 4" and 3"
duct rings on the other side (12.7cm, 10.2cm and 10.2cm, 7.6cm respectively).

Key Benefits (continued)■

Versatile ABS plastic transitions and boxes
feature off-the-shelf availability and are
vacuum formed for consistent quality.

■

ABS plastic T-boxes have insulated
mounting pads, unique stepped ring designfor flexibility, and feature off-the-shelfavailability.

Aluminum Transitions:• Opening dimensions are 0.25" (0.64cm) larger than transition size (i.e., 10" X 5"
AL has a 10.25" X 5.25" opening. 25.4cm x 12.7cm AL has a 26.0cm X 13.3cm
opening).
• Flange to flange dimensions are 1.75" (4.4cm) larger than transition size (i.e.,10"
X 5" AL = 11.75" X 6.75". 25.4cm X 12.7cm AL = 29.8cm X 17.1cm).
• Depth of AL transition box is 0.25" (0.64cm) longer than the diameter of largest
round ring (measured from back of flange).
• Flange dimensions are 0.75" (1.9cm) on all sides.
Obround Rings Dimensions:• 3"OB =3.875" X 1.625" (9.84cm X 4.13cm)• 4"OB =5.125" X 2.250" (13.02cm X 5.72cm)• 5"OB =6.500" X 2.625" (16.51cm X 6.67cm)• 6"OB =7.438" X 3.375" (18.89cm X 8.57cm)• 7"OB =9.000" X 3.625" (22.86cm X 9.21cm)• 8"OB =9.250" X 5.000" (23.50cm X 12.70cm)• All obround rings are made of ABS plastic, except the 8"OB which is made ofaluminum. Add 0.25" (0.64cm) to obround dimensions for minimum box size. Allrings are 2.0" (5.1cm) deep.
VF = Vacuum Formed

AL = Aluminum

Supply Air Transition Box(Typical)Remote Box

DEBFacingThis View

TRANSITION BOXESC
VF T-Box

NOTE: Letters denotelocation of rings whenordering boxes. See orderform found in ID: 2163
Marine Air DX price schedule.

A

Transition Ring
E
E

Round

B

A
B

Obround
DCF

DUCTINGD
FacingThis View

F
ENCLOSED BOX
TO FIT UNIT

TRANSITION RINGSENCLOSED REMOTE BOX

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2131 Rev. 20080829

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:N 50How z
Av Mo
a i dela lsble!

Dometic Marine Air Conditioning

Dometic EnviroComfort Kit

Climate Control at the Touch of a Button

Dometic EnviroComfort
15,000 BTU/hr Kit

Enjoy ideal temperatures in your boating environment year-round with
Dometic’s EnviroComfort air conditioning systems. We offer a wide range of

Key Benefits
Cools and heats.

capacities from 5,000 to 15,000 BTU/hr, so you can size the system to suit your boat for■

ultimate cooling and heating comfort. All EnviroComfort models use R-417A refrigerant,■

Available in 50Hz and 60Hz models.

an environmentally safe gas.

■High velocity, rotatable blower forhorizontal or vertical installation.

The EnviroComfort kit includes everything needed for a professional installation on■

Green gas (R-417A).

boats with or without an existing air conditioning system.

■

Compact Dometic digital-display control.

■

Plastic remote electrical box forconvenience in mounting.

■

Stainless-steel drain pan.

■Pre-installed return-air filter, easily
removable and cleanable.

■

Small, compact, space-saving design.

■

Complete kit - All pieces, parts, andpumps (from seawater intake to supplyair grille).

■

Optional dual-duct kit for models 6.5K
BTU/hr and higher (details on reverseside).

■

Available capacities (in BTU/hr): 5,000,
6,500, 9,000, 11,000, and 15,000.

■

Replaces Cabin Mate.

EnviroComfort units use high-velocity blowers that eliminate blower-motor overhang
for a smaller installation footprint. For flexibility in connecting to ductwork, the blower isrotatable to either a horizontal or vertical position. The compact, space-saving design
is contained in a stainless-steel drain pan, and the pre-installed return-air filter is easily
removable and cleanable.
For system operation, EnviroComfort kits include a compact Dometic digital-display
control. For added installation convenience, the plastic electrical box can be mounted
remotely.
For applications requiring an additional air outlet,
Dometic’s dual-duct kit (shown at left) is available
for EnviroComfort models with BTU/hr capacitiesof 6.5K and higher.

ISO 9001:2008
L–2628

Rev. 20100806

81

82

Dometic Marine Air Conditioning

Technical Specifications for Dometic EnviroComfort Air Conditioners
Model

ECD05

ECD06.5

ECD09

ECD11

ECD15

Capacity (BTU/hr)

5,000

6,500

9,000

11,00015,000Power (Volt/Hz/Ph)

115/60/1

220/50/1

115/60/1

115/60/1

115/60/1

220/50/1

115/60/1

Full Load Amps - Cool

3.8

2.2

5.4

6.3

6.8

3.7

10.0

4.5

Full Load Amps - Heat

5.0

2.9

7.0

8.6

9.4

4.7

13.0

5.8

Locked Rotor Amperage

29.0

53.0

22.2

67.0

40.0

49.0

R-417A

R-417A

R-417A

R-417A

R-417A

Dometic Digital

Dometic Digital

Dometic Digital

Dometic Digital

Dometic Digital

Height (in/mm)

11.75/298

11.75/298

13.50/343

13.50/343

13.50/343

Width (in/mm)

9.50/2419.50/2419.75/248

9.75/248

11.00/279

Depth (in/mm)

17.75/451

19.75/502

21.75/552

21.75/552

21.75/552

0.63/16

0.63/16

0.63/16

0.63/16

0.63/16

Net weight (lbs/kg)

39.0/17.7

44.0/19.6

58.0/26.3

57.0/25.9

64.0/29.0

Ship weight (lbs/kg)

TBD

TBD

TBD

TBD

TBD

Refrigerant type
Control type11.0

220/50/1

32.0

Dimensions (± 0.5" or 13mm)

Connections
Sea Water (in/mm)
Estimated Weight(1)Notes:(1)

Digital Control and Thermostat

Weights listed are for ECM units only and do not include kit components.

Discharge Grille

Insulated Flex Duct

HeightTo AC
PowerConnection
Dometic Marine Climate
Self-Contained AC Unit

Width

Overboard Discharge

Depth

"
6.50
mm
165

Dimensions for remote-mountable elec"
8.75
mm
222

Condensate Drain

trical box for all ECD models.

Return Air
GrilleRemoteElectrical Box

2.77"
70 mm

SeawaterSupply Line

Seawater
Pump

Valve
Seawater
Strainer
Thru-hull
Fitting

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2628 Rev. 20100806

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:N 50How z
Av Mo
a i dela lsble!

Dometic Marine Air Conditioning

83

Dometic EnviroCool Kit

Climate Control at the Touch of a Button

Dometic EnviroCool
5,000 BTU/hr Kit

Enjoy ideal temperatures in your boating environment with Dometic’s
EnviroCool Series of marine air conditioning kits. The EnviroCool Series offers

Key Benefits

a wide range of BTU capacities from 3,500 to 15,000 BTU/hr to allow you to size your■

Small, compact space-saving design.

system for ultimate cooling. The EnviroCool series uses environmentally safe R-134A■

Stainless-steel drain pan.

(3.5K BTU/hr. model) and R-417A (5K - 15K BTU/hr. models) refrigerants.

■

Available in 50Hz and 60Hz models.

■Green gas (R-134A and R-417A).

■

Two-knob mechanical control.

■

Complete air conditioning kit - All pieces,parts, and pump.

■High velocity, rotatable blower - either
horizontal or vertical positions.

■Pre-intalled return-air filter, easily
removable and cleanable.

■

Optional dual-duct kit for 6.5K BTU/hr andup models (details on reverse side).

■

Available capacities (in BTU/hr): 3,500,
5,000, 6,500, 9,000, 11,000, and 15,000.

■

Replaces Cool Mate and Zephyr.

The EnviroCool kit includes everything needed for a professional installation on boats
with or without an air conditioning system.
EnviroCool units use high-velocity blowers that eliminate blower-motor overhang fora smaller installation footprint. For flexibility in connecting to ductwork, the blower isrotatable to either a horizontal or vertical position. The compact, space-saving design
is contained in a stainless-steel drain pan, and the pre-installed return-air filter is easily
removable and cleanable.
For system operation, EnviroCool uses a two-knob mechanical switch for reliable
control over air conditioner functions.

ISO 9001:2008
L–2631

Rev. 20100806

84

Dometic Marine Air Conditioning

Technical Specifications for Dometic EnviroCool Air Conditioners
Model

ECM03.5

ECM05

ECM06.5

ECM09

ECM11

Capacity (BTU/hr)

3,500

5,000

6,500

9,000

11,000Power (Volt/Hz/Ph)

115/60/1

115/60/1

220/50/1

115/60/1

115/60/1

115/60/1

220/50/1

115/60/1

Full Load Amps - Cool

4.3

3.8

2.2

5.4

6.3

6.8

3.7

9.4

4.5

Locked Rotor Amperage

14.0

29.0

11.0

40.0

49.0

53.0

22.2

59.0

32.0

Refrigerant type
Control type

ECM15
15,000220/50/1

R-134A

R-417A

R-417A

R-417A

R-417A

R-417A

Mechanical

Mechanical

Mechanical

Mechanical

Mechanical

Mechanical

Dimensions (± 0.5" or 13mm)
Height (in/mm)

9.50/24111.75/298

11.75/298

13.50/343

13.50/343

13.50/343

Width (in/mm)

9.75/248

9.50/2419.50/2419.75/248

9.75/248

11.00/279

Depth (in/mm)

17.75/451

17.75/451

19.75/502

21.75/552

21.75/552

21.75/552

0.63/16

0.63/16

0.63/16

0.63/16

0.63/16

0.63/16

Connections
Sea Water (in/mm)
Estimated Weight(1)Net weight (lbs/kg)

25.0/11.3

39.0/17.7

45.0/20.4

54.0/24.5

54.0/24.5

60.0/27.2

Ship weight (lbs/kg)

32.0/14.5

50.0/22.7

TBD

TBD

TBD

72.0/32.7

Notes:(1)

Control Switch and Thermostat

Weights listed are for ECM units only and do not include kit components.

Discharge Grille

Insulated Flex Duct

HeightTo AC
PowerConnection
Dometic EnviroCool
Self-Contained AC Unit
Width

Overboard Discharge

Depth

Condensate Drain
Return Air Grille

SeawaterSupply LineValve
Seawater
Pump

Dual-Duct Kit

Seawater
Strainer

For applications requiring an additional air outlet,
Dometic’s dual-duct kit is available for 6.5-15K
BTU/hr EnviroCool models.

Thru-hull
Fitting

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2631 Rev. 20100806

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Dometic Marine Air Conditioning

85

DuraSea Condensing Units

Designed for Maximum Durability

2-YEARCOMPRESSOR

LIMITEDWARRANTY

DCA60D shown; optionalrisers not shown

1-YEARPARTS

Dometic DuraSea air conditioning condensing units are designed for
maximum durability in the harshest of nautical applications. These rugged

Key Benefits

units offer long service life, exceptional performance, energy conservation, and reliability.

■ Designed specifically for the rugged workboat

The DuraSea’s cabinet is constructed of stainless-steel 304, which resists heavy salt-■ Operates with most air handler units.

spray and also provides UV protection. Designed for deck or rooftop mount, the optional■ Hermetically sealed scroll compressor withrisers elevate the unit above the mounting surface to provide excellent water drainage
and protect the coil from debris and salt water. To further fortify the unit from severemarine conditions, corrosion-resistant stainless-steel fasteners are used, and all otherexternal components have a protective coating. The control box and compressor are
strategically located within the cabinet for easy service access and for extra protection
against corrosion.

compressor technology. They reduce noise andvibration, and have a higher tolerance of liquid
refrigerant and system contaminants. Scroll
compressors also feature low start torque to minimize
the starting-current spike that occurs with oldtechnology compressors.

L–2544

Rev. 20090429

internal overload protection.
■ Permanently lubricated condenser fan motorwith VIP Vacuum Impregnated windings.
■ High-efficiency copper tube/aluminum fin coilwith dipped coating that exceeds 1000-hoursalt spray test.
■ Copper tube/copper finned coils are available

All DuraSea units employ scroll compressors, the latest in high-efficiency, reliable

ISO 9001:2008

market.

for ultimate protection.
■ Brass base valves with sweat connections andservice ports.
■ Vertical fan-mount design.
■ High- and low-pressure controls.
■ Heavy-duty contactor with lug connections.

86

Dometic Marine Air Conditioning

Technical Specifications for DuraSea Condensing Unit (Standard Models)Model

DCA36D

DCA36E

DCA48D

DCA48E

DCA60D

DCA60E

DCA72D

DCA72E

DCA90D

DCA90E

DCA120D

DCA120E

Capacity (BTU/hr)

36,00036,00048,00048,00060,00060,00072,00072,00090,00090,000120,000

120,000

RLA

9.7

4.9

12.7

6.5

16.7

8.3

20.7

10.0

32.1

16.4

42.0

19.2

LRA

77

39

91

50

128

63

156

70

195.0

95.0

239.0

125.0

MCC

16

8

23

11

29

14

29

14

45.0

23.0

58.9

26.9

CFM

6000

6000

6000

6000

6000

6000

6000

6000

6000

6000

10000

10000

Motor FLA

3.6

2.0

3.6

2.0

3.6

2.0

3.6

2.0

3.6

2.0

8.5

4.9

Liquid Valve Size (OD) (1)

3/8"

3/8"

3/8"

3/8"

1/2"

1/2"

1/2"

1/2"

1/2"

1/2"

5/8"

5/8"

Suction Valve Size (OD) (1)

3/4"

3/4"

7/8"

7/8"

7/8"

7/8"

7/8"

7/8"

1-1/8"

1-1/8"

1-3/8"

1/3/8"

Refrigerant Charge

80

80

80

80

120

120

120

120

150

150

150

150

Volts/Hz/Phase208-230/
60/3

460/
60/3

208-230/
60/3

460/
60/3

208-230/
60/3

460/
60/3

208-230/
60/3

460/
60/3

208-230/
60/3

460/
60/3

208-230/
60/3

460/
60/3

Min. Circuit Amps (2)

16

8

20

10

25

15

30

15

45

25

65

30

Max. Breaker Protection (3)

20

15

30

15

40

20

40

20

60

30

80

35
414/506

197/253

414/506

197/253

414/506

197/253

414/506

197/253

414/506

197/253

414/506

197/253

Sound Level (dbA) (4)Min./Max. Volts

84

84

84

84

84

84

84

84

84

84

87

87

Unit Weight (lbs/kg) (5)290/132

290/132

310/141

310/141365/166

365/166

375/170375/170475/215475/215525/238525/238

Notes:Up to 50' (15.2 m) in equivalent line length.
Wire size should be determined in accordance with National Electric Codes. Extensive wire runs require larger wire sizes.
Must use time-delay fuses or HACR type circuit breakers of the same size as noted.
(4)Sound level measured at 3' (0.9 m) away from condensing unit.
(5)
Weight for aluminum fin condenser coil with coating.
(1)
(2)
(3)

*In the interest of product improvement, all data is subject to change at Dometic’s discretion.

DCA Dimensions (Standard Models)
Model
DCA36

Width

Dimensions (in/mm)
Depth
Height33.0/838

33.0/838

DuraSea is available in custom configurations byspecial request (slim profile shown)

38.5/978

DCA48

33.0/838

33.0/838

38.5/978

DCA60

33.0/838

33.0/838

38.5/978

DCA72

33.0/838

33.0/838

38.5/978DCA90

33.0/83848.0/1219

42.0/1067

DCA12033.0/83848.0/1219

42.0/1067

24.0"

54.0"

45.0"

Commitment to Quality
Built with quality inside and out by Dometic, the world leader in marine
tio n

ag

e

m

ABYC and USCG regulations, CE directives, and general ARI standards.

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2544 Rev. 20090429

Environmentally
Responsible

Specifications and availability subject to change without notice.

en

tifi
ca

★ AB
S
M an

charged and thoroughly run tested. DuraSea units meet or exceed

lity Evaluation
ua
Q

.★
Inc
s,

air conditioning for 50 years. Every DuraSea condensing unit is factoryt S y st e m C

er

ISO 9001:2000
Certificate #34104

Dealer:Dometic Marine Air Conditioning

87

Radome Environmental Control Units

Keep Your Equipment Cool

Self-contained
HSA16KCZ/1-417A shown

Safe navigation relies on your ship’s radar and communications equipment, and as with all electronics, overheating leads to equipment failure. The Radome Environmental Control Unit (ECU) is specifically designed to workwithin the dome enclosure, ensuring optimum temperatures for the critical equipment
inside.

Key Benefits■ 3 configurations: Self-contained interior dome,

self-contained remote ducted, and split-gas.
■ Compact, lightweight, and easy to install.
■ Durable, corrosion-resistant coating.

As you would expect from the world leader in marine air conditioning technology, thisair-cooled unit is built for at-sea conditions. Although small and lightweight to provide
ease of installation and maintenance, the Radome ECU is designed to exceed thecooling requirements of pleasure boat, commercial vessel, and military ship applications. Rugged construction with corrosion-resistant materials allows the unit to be
operated in the most extreme conditions at sea.
The Radome ECU’s highly efficient yet powerful rotary compressor provides quieter
operation, increased reliability, and reduced amperage. Its raised-lance fin and therifled tubing design of the evaporator and condenser coils provide maximum capacity.
Three configurations are offered: interior dome self-contained, remoted ducted selfcontained, and split-gas.
The Radome ECU is not limited to marine applications. It can also control the temperature and humidity levels of on-land locations such as electronics enclosures, telecommunications shelters, vaults, buildings, trailers, vans, and cleanrooms.

■ Available in R-417A environmentally-safe

refrigerant.
■ R-22 units are retrofittable to R-417A to meetglobal environmental regulations.
■ Solid state digital control provides reliable

monitoring and control.
■ Control circuitry monitors and protects the unit.
■ High-efficiency rotary compressors provide

reduced amperage, quieter operation, lower
weight, and increased reliability.
■ Raised lance fin and rifled tubing for maximum

capacity.
■ Each unit is pre-charged and leak checked.
■ Charge Guard ® protection provides sealed

access ports, ensuring environmental
protection and system integrity.
■ Meet or exceed applicable ABYC and U.S.

Coast Guard regulations, CE directives, andgeneral Air Conditioning and Refrigeration
Industry (ARI) standards.

ISO 9001:2008
L–2132

Rev. 20090717

88

Dometic Marine Air Conditioning

Technical Specifications for Radome Environmental Control Units
Model

Radome ECU Unit

Capacity (BTU/hr)

ECU Evaporator Unit

16,000

Voltage/Hz/Ph

115/50-60/1

230/60/1(1)220/50/1

67.0

29.0

32.0

Locked Rotor Amps (Comp)
K.V.A. (Kilo-Volt-Amps)

1.3

1.3

1.3

Max. Circuit Breaker (Amps)

40.0

20.0

20.0

Min. Circuit Ampacity

25.0

14.0

12.0

R-417A Refrigerant (oz/g)

26/737

Net Weight (lbs/kg)

95.0/43.1

Gross Weight (lbs/kg)

130.0/59.0

ECU Condensing Unit

Dimensions

30.0" X 18.0" X 14.5"762mm X 457mm X 368mm

Radome ECU split-gas system shown above

Split (LxWxH) (3)Self-Contained (LxWxH) (2)Condenser

Air Handler

17.5" X 18.0" X 14.5"445mm X 457mm X 368mm

12.7" X 18.0" X 14.5"323mm X 457mm X 368mm

Notes:(1)(2)(3)

Can also be operated at 200-220V/50Hz.
Allow 1.5" (38mm) for mounting brackets.
Rotary compressors only.

The Radome ECU is available in three configurations:

ECU
Evaporator
Return Air
Duct
Supply Air
Duct

ECU
Condenser

Split-gas configuration

ECU

Remote ducted self-containedInterior dome self-contained(ideal for low pedestal applications)(Exhaust kit is available for low
pedestal applications to correctcondenser air short cycling)

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2132 Rev. 20090717

ECU

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:Eskimo Ice Fishbox Ice Systems

Eskimo Ice Fishbox Ice Systems

For Serious Tournament Anglers■ Keep your catch fresh all day.

EI600D-115 SelfContained Model

Crushed ice—preferred by fishermen—cools more quickly and packs
better. A Dometic Eskimo Ice system produces up to 600 pounds (272 kg) of crushed

Key Benefits

ice per day to keep even the largest catches fresh. Ice is generated within minutes after■

Available in 60Hz or 50Hz.

starting the unit, and makes up to 25 pounds (11.3 kg) of ice per hour under normal■

Self-contained and remote models
available with Smart Logic digital
control.

■

Up to two remotely mounted digital
displays/user interface panels.

through hose lengths up to 30 feet (9.1 meters) to nearly any desired location onboard,■

Photo-electric ice-level sensor.

such as a fish box or cooler.

■

Start-time delay.

■

Fresh water filter included.

All self-contained and remote Eskimo Ice systems feature the■Pre-charged system.

Smart Logic Digital Display. A full menu of sensors and status lights■

Sensors monitor all system functions.

■

Manual reset to restart system fromlock-out.

detected. The system automatically resets and restarts for certain■

Improved fresh-water float switch.

key functions that can be triggered by extreme boat motion.

■

Redesigned refrigerant meter for
improved performance in cold water.

■

Optional side and top covers forprotection and improved appearance.

operating conditions.
The easy-to-install Eskimo Ice system is designed to be mounted below deck or in anengine room where it is protected from salt spray. The ice it produces can be pumped

monitor gas pressure, auger motor, compressor, water level, icelevel, and ice clogs, and will shut off the system if problems are

Available in either 60Hz or 50Hz versions. Digital-control retrofit kits
are available.

ISO 9001:2008
L–2450Rev. 20110211

89

90

Eskimo Ice Fishbox Ice Systems

Technical Specifications for Eskimo Ice 600 Series
Water
Consumption

Dimensions (in/mm)

Volts/Freq/Ph

Running
Amps

LRA

EIR600-115 Condensing Unit

115/60/1

14.0

66.3

N/A

N/A

12.88/327

EIR600-115 Auger Unit

115/60/1

2.0

N/A

600 lb/day

60 gal/day

14.25/362

Model

Capacity (1)Height

Net Weight(lb/kg)12.88/327

15.00/381

67/30.5

16.38/416.1

20.88/530.4

83/37.7

Width

Depth

Remote Systems

EIR600-230 Condensing Unit

230/60/1

7.0

33.5

N/A

N/A

12.88/327

12.88/327

15.00/381

67/30.5

EIR600-230 Auger Unit

230/60/1

1.0

N/A

600 lb/day

60 gal/day

14.25/362

16.38/416.1

20.88/530.4

83/37.7
67/30.5

EIR600-220 Condensing Unit

220/50/1

6.5

40.0

N/A

N/A

12.88/327

12.88/327

15.00/381

EIR600-220 Auger Unit

220/50/1

1.0

N/A

500 lb/day (2)60 gal/day

14.25/362

16.38/416.1

20.88/530.4

83/37.7

Remote Electrical Box

N/A

N/A

N/A

N/A

N/A

9.25/234

5.38/136

6.38/162

4.00/1.81

EI600D-115

115/60/1

16.0

66.3

600 lb/day

60 gal/day

17.50/445

23.50/597

22.00/559

135.00/61.4

EI600D-230

230/60/1

8.0

33.5

600 lb/day

60 gal/day

17.50/445

23.50/597

22.00/559

135.00/61.4

EI600D-220

220/50/1

7.5

40.0

500 lb/day

60 gal/day

17.50/445

23.50/597

22.00/559

135.00/61.4

Self-Contained Systems(2)

Notes:(1)
Capacity ratings depend upon conditions.
(2)
Rated at 500 (227 kg) lbs per day because of 50Hz derate.

The Eskimo Ice basic kit includes:• Ice Machine with condensate pan.
• 15' (4.5m) of ice-delivery hose and insulation.
• Electronic ice-level control unit.
• Complete installation instructions.
• Fresh water filter

EI600D Split System Installation
Ice Delivery Hose:
1-1/4" I.D. x 1-3/4" O.D.
Hose Length 1' - 30' Insulated
Fish
Box

Condensing Unit
Pump
Seawater Strainer

ENGINE ROOM
Auger Unit

Water
Line

Linesets

Water Filter

Overboard
Discharge

Thru-Hull Fitting

Fresh Water
Supply Line

Seawater Supply Line

Mid-ShipFresh Water
Tank

Water
Line

EI600D Self-Contained System Installation

Ice Delivery Hose:
1-1/4" I.D. x 1-3/4" O.D.
Hose Length 1' - 30' Insulated
Fish
Box

Water
Line

ENGINE ROOM
Overboard
Discharge

Self-Contained Unit
Pump
Seawater Strainer

Fresh Water
Supply Line

Seawater Supply Line

Fresh Water
Tank

Water Filter
Thru-Hull Fitting

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2450 Rev. 20110211

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:

Water
Line

N 50How z
Av Mo
ai d ela lsble!

Eskimo Ice Fishbox Ice Systems

91

Ice Cube Fishbox Ice System

Produces Up to 250 Lbs. of Ice a Day■ Keep your catch fresh all day.

EI250D-115 shown

The Ice Cube – A Smaller Crushed-Ice System
Dometic Eskimo Ice is available in a smaller version—the Ice Cube—for boats with less

Key Benefits■

Small footprint—16" x 16" (413mm x
413mm).

16" (413mm x 413mm), the Ice Cube makes up to 250 lbs. (113 kg) of crushed ice per■

Available in 50Hz and 60Hz models.

day. Ice is generated within minutes after starting the unit, and makes more than 10 lbs.

■

Up to two remotely mounted digital
displays/user interface panels.

■

Photo-electric ice-level sensor.

■

Start-time delay.

■

Water filter included.

■

Pre-charged system.

■

Sensors monitor all system functions.

■

Manual reset to restart system after lockout.

and will shut off the system if problems are detected. But■

Improved fresh-water float switch.

the system automatically resets and restarts for certain■

Ventilated cover panels are removablefor servicing from virtually any side of theunit.

space or less demand for daily ice output. Cube-shaped, with a footprint of only 16" x(4.5 kg) of ice per hour under optimal operating conditions.
The Ice Cube is a self-contained unit and easy to install. The ice it produces can bepumped through insulated hose lengths up to 15' (4.5m), to nearly any desired location
onboard, such as a fish box or cooler.
Operation of the Ice Cube is easy with its Smart Logic Digital Displays. A full menu of
sensors and status lights monitor gas pressure, auger
motor, compressor, water level, ice level, and ice clogs,

key faults.

ISO 9001:2008
L-2617

Rev. 20090821

92

Eskimo Ice Fishbox Ice Systems

Technical Specifications for Ice Cube
Model
Capacity per day (lbs/kg)
Capacity per hour (lbs/kg)
VoltageFrequency
Full Load Amps (FLA) Cool
Locked Rotor Amps (LRA)
Refrigerant
Water consumption, gallons per day
Water consumption, liters per day
Dimensions
Height (in/mm)
Width (in/mm)
Length (in/mm)
Connections
Sea water (in/type)
Fresh water (in/type)
Weight
Net weight (lbs/kg)
Shipping weight (lbs/kg)

EI250D-115

250/113(1)>10.42/>4.73 (1)SeawaterOutlet

115
60Hz
9.68
40.00
R-134A
30 @ 250 lbs
113.56 @ 113.4
16.25/413
16.25/413
16.25/413
5/8"/hose barb
1/4"/SAE

Seawater
Inlet
Condensate
Drain82.0/37.2
97.0/43.9

Recommended Ice Cube System Installation

Ice Delivery Hose:
1-1/4" I.D. x 1-3/4" O.D.
Hose Length 1' - 15' Insulated

Water
Line

Opening forElectrical

The Ice Cube basic kit includes:

Under optimal conditions.

Fish
Box

Fresh Water
Supply

220
50Hz
4.50
14.80

Notes:(1)

Opening forIce Delivery Hose

EI250D-220V/50

Overboard
Discharge

Fresh Water
Supply Line

Water Filter

ICE
CUBE
Pump
Seawater Strainer• Ice Cube ice-making system.
• (1) Smart Logic digital display.
• Water filter.
• 15' (4.5m) of ice-delivery hose and insulation.

Fresh Water
Tank

ENGINE ROOM
Seawater Supply LineThru-Hull Fitting
Mid-Ship

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–2617 Rev. 20090821

Environmentally
Responsible

Specifications and availability subject to change without notice.

Dealer:For new products and older products (still available on special request), please go to www.dometic.com/marineair or call 954-973-2477. This booklet of
specification sheets is provided to you for inspection of products. Realize that these sheets contain data that is time-sensitive and subject to change without
notice. Changes are made on these sheets periodically as models are improved. We thank you for your interest in Marine Air.

Certified Worldwide Sales & Service Network

Represents sales
and service
coverage range

DOMETIC MARINE DIVISION
2000 N. Andrews Ave. Ext. l Pompano Beach, FL 33069 USA l 954-973-2477 l Fax 954-979-4414
www.DometicUSA.com l MarineSales@DometicUSA.com
24/7 Tech Support for United States & Canada:
8:00 AM to 5:00 PM Eastern Time: 800-542-2477
After hours and weekends: 888-440-4494
International Sales & Service:
Europe & the Middle East: Call +44(0)870-330-6101
For all other areas visit our website to find your nearest distributor.
L–0002 Rev. 20110422

ISO 9001:2008

Environmentally
Responsible

Dealer: