PowerShield8
Battery management system
PowerShield8システムは、大規模なバッテリーシステムと小規模なバッテリーシステムの両方を対象としたハードウェアオプションにより、無制限の数のバッテリーを監視することができます。ハードウェアのオプションは、大規模および小規模のバッテリーシステムを対象としています。ハードウェアとソフトウェアの完全なソリューションは、バックアップバッテリーがIEEE/IECガイドラインの範囲内で動作していることを確認するために必要な情報を得ることを保証します。バックアップバッテリーがIEEE/IECガイドラインの範囲内で動作していることを確認するために必要な情報を得ることができます。

System specifications
Capability

Controller LX

Controller MX

up to 512 blocks

up to 200 blocks

up to 8 strings*

up to 4 strings*

Controller LX
Interfaces

Controller MXLink Battery Management Software
Controller Web Interface
16 x 2 character LCD & keypad

Battery system
information

Block : 電圧、リップル電圧、Ω、温度

Communication ports

String : 電圧、電流、リップル電流
Environment: 周囲温度、湿度
鉛酸 (2V, 4V, 6V, 8V, 12V & 16V)

Battery types–2 x 1000Base-T Ethernet

1 x 1000 Base-T Ethernet

2 x Expansion ports - RS485(optional)

1 x USB

Protocols

1 x Expansion ports - RS485(optional)

ModbusTCP, SNMP and HTTP

Ni-Cd (1.2V, 3.6V)

ModbusRTU when RS485 card is fitted

Battery charging
regimeFloat and Intermittent

Relay outputs

41

Thermal runaway
management

String breaker or charger step down signalling

Digital inputs

up to 10up to 4 via Hubs*

Environment

Operating temperature: 0 to 50°C / 32 – 122°F

2 via Controller, up to 8 via
Hubs

Certifications

Storage temperature: -10 to 70°C / 14 – 158°F
10 to 90% RH non condensing
Altitude: 2000m max. , Indoor use only.

Controller
Service port

Controller LX

Controller MX

Front Ethernet port(1000Base-T)

USB 2.0 (Type B)

Port 1

Back Ethernet port (1000Base-T)

Port 2
Port 3
Display

Controller LX
Dimensions
WidthDepth
Height1U High 19” rack mountPower supply

Controller MX

430mm / 16.9 inches

250mm / 9.84 inches

265mm / 10.4 inches

155mm / 6.1 inches

45mm / 1.8 inches

36mm / 1.4 inches

AC Model: 90 – 260V 50/60Hz

AC Model: 90 – 260V 50/60Hz

24V DC Model: 18 – 30V

48 DC Model: 18 – 60V

48V DC Model: 35 – 60V

110 DC Model: 80 – 150V

Expansion port - optional RS485
Expansion port - optional
RS485–16 x 2 character LCD–

110V DC Model: 80 – 150V

Front

USB data storage

SD Card data storage

Power consumption

5W + 1.2W per Hub

Relay outputs

4 SPDT

1 SPDT

Digital inputs

2 (Voltage free / Dry contact)

Memory2GB RAM512MB RAM

4GB Flash

4GB FlashRating

1.5W + 1.2W per Hub–

1A @ 30VDC, resistive*
Any relay configurable to any alarm

Selectable
Configuration interface

Web browser

Minimum version

Chrome 50, Firefox 45, Safari 6.1, Internet Explorer 10, Edge 12*Contact PowerShield for further details.

powershield.com

PowerShield8 Battery Management System

Link battery management software
Minimum PC system requirements1

1

Processor

Intel i3-6100 or faster

RAM8GB

Operating system

Windows 10

Storage

20GB available hard disk space

Windows Server 2012, 2012 R2, 2016

Monitor1024 x 768 or 1366 x 768

最大5台までのコントローラー接続、シングルシート操作を推奨。より大規模な構成については、PowerShieldを参照してください。

mSensorDual and Single Input
鉛酸 (2V, 4V, 6V, 8V, 12V & 16V)

Battery typeNi-Cd (1.2V, 3.6V)

Nominal voltage

1NiCad2

2V6V

12V

Operating range

0.8V-1.9V

1.6V-2.6V

4.8V-7.8V

9.6V-15.6V

Maximum input voltage

±5V

±6V

±25V

±65V

DC resolution / accuracy

1mV / ±0.3%

1mV / ±0.3%5mV / ±0.2%

5mV / ±0.2%

AC resolution

1mV

1mV

1mV

1mV

0.10-5mΩ

0.10-5mΩ

0.50-20mΩ

1.00-40.00mΩ

1uΩ / ±2.5% + ±15uΩ

1uΩ / ±2.5% + ±15uΩ

1uΩ / ±2.5% + ±25uΩ

1uΩ / ±2.5% + ±25uΩ

Ohmic measurement range
Resolution / accuracy
Temperature3-10 to 70°C / 14 to 158°FRange

0.1°C / ±1°C

Resolution / accuracy
Power supply current450mA

30mA

18mA

1Most common models, other models available on request

3

Operating temperature -10 to 50°C / 14 to 122°F

2

Ni-Cd single 1V mSensor cannot perform ohmic measurement

4

Power by block being monitored

18mA
Design rated to 750VDC. UL certified to 600Vdc

The mSensor communicates via Modbus, meaning it can be easily integrated with other Modbus based site management systems.
Contact PowerShield for further details.

HubPowered

24Vdc supplied by Controller

Power consumption

1.2W

Digital inputs

1, voltage freeRelay outputs

1

DC current1

0 - 2000A (Hall Effect sensor)

Temperature-10 to 80°C / 14 to 176°F

Typical resolution

0.05A

Resolution

0.1°C / 0.18°F

Accuracy±1% + CT accuracy

Accuracy±1°C / 1.8°F

Relative humidity

0 - 100%

Ripple current (AC)11

True RMS

Typical resolution

0.5A

Resolution

1.0%Accuracy±1% + CT accuracy

Accuracy

20% - 80% ±3% at 25°C / 77°F

Frequency range

10 – 1000Hz*Contact PowerShield for further details.

Resolution dependent on CT model used, typical values are based on 400A CT

Installation Dimensions
Dimension

Maximum

AB

Factory sizes

MetresFeet

Metres

Feet

A

75

246

--

B

50

164

3, 5, 10, 15

10, 16, 33, 49

C

2582

--

D1549

3

10E-

-

0.2, 0.4, 0.7, 1.0

8, 16, 28, 39 inches

Controller

Cat 5/6C4 coreflat

HubmSensor

mSensorED
PS8DS_v2.4_2019

powershield.com

powershield.com