-|Transparent Guide|-᜸ Caution Failure to follow instructions may result in injury or product damage.

01. Use the unit within the rated specifications.
Failure to follow this instruction may result in fire or product damage.
02. Use a dry cloth to clean the unit, and do not use water or organic solvent.
Failure to follow this instruction may result in fire or electric shock.
03. Keep the product away from metal chip, dust, and wire residue which flow into theunit.
Failure to follow this instruction may result in fire or product damage.
04. Do not use the product when a screw of terminal is loosened.
Failure to follow this instruction may result in fire or product damage.

Cautions during Use• Follow instructions in ‘Cautions during Use’. Otherwise, it may cause unexpected accidents.
• Check the polarity of power or COMMON before connecting PLC or other controllers.
• Do not touch the unit immediately after the load power is supplied or cut.
It may cause burn by high temperature.
• 24VDCᜡ power supply should be insulated and limited voltage/current or Class 2, SELV power
supply device.
• Wire as short as possible and keep away from high voltage lines or power lines, to prevent surge
and inductive noise. Do not use near the equipment which generates strong magnetic force orhigh frequency noise (transceiver, etc.). In case installing the product near the equipment which
generates strong surge (motor, welding machine, etc.), use diode or varistor to remove surge.
• This unit may be used in the following environments.
- Indoors (in the environment condition rated in ‘Specifications’)- Altitude max. 2,000 m- Pollution degree 2- Installation category II• 4-point model: 4-pin 7.62 mm pitch jumper bar (JB-7.62-04)
16-point model: 8-pin 7.62 mm pitch jumper bar (JB-7.62-08)

Sold Separately• 7.62 mm pitch jumper bar (4-pin: JB-7.62-04, 8-pin: JB-7.62-08)• I/O cable• Two Way Ejector

ABS-H32□-□

Output method

1a1a1aPA: ≤ 8 mA 02)
TN: ≤ 8.5 mA 02)

PA: ≤ 8 mA 02) or ≤ 13 mA 03)
TN: ≤ 8.5 mA 02) or ≤ 13.5 mA 03)

PA: APAN3124 [MATSUSHITA (Panasonic)] / TN: NYP24W-K [TAKAMISAWA (Fujitsu)]≤ 24 VDCᜡ ±10 %Current
consumption

250 VACᜠ 3A,30 VDCᜡ 3A

Rated load voltage &current 04) 05)-Connector forcontroller side

-4

No. of relay points

Screw

Terminal type7.62 mm

Terminal pitch≤ 24 VDCᜡ ±10 %250 VACᜠ 2A,30 VDCᜡ 2A

20-pin Hirose(HIF3BA-20PA-2.54DSA)

40-pin Hirose(HIF3BA-40PA-2.54DSA)

2032 (8점/1COM)

Screw

7.62 mmᜢ ᜨ ᜫ 06)

PA: ≈ 68 g (≈ 104 g)
TN: ≈ 71 g (≈ 107 g)

Unit weight(packaged)

PA: ≈ 224 g (≈ 307 g)
TN: ≈ 235 g (≈ 318 g)ᜢ ᜨ ᜫ 06)

PA: ≈ 345 g (≈ 438 g)
TN: ≈ 370 g (≈ 463 g)01) For the detailed information about each relay, please refer to ‘Power Relay’ or data sheet from the manufacturer.
02) It is current consumption for a relay including LED current.

03) It is current consumption including LED current for power part to 2).
04) This value is rated with resistive load.

05) When connecting loads to output part, please connect loads of same power type.
Connecting loads of different power type may cause safety issues.
06) 30 VDCᜡ of rated load voltage is not subjected to UL Listed.

Insulation resistance≥ 1,000 MΩ (500 VDCᜡ megger)

Dielectric strength(same polarity contact)

PA: 1,000 VACᜠ 50/60 Hz for 1 minute
TN: 750 VACᜠ 50/60 Hz for 1 minuteDielectric strength(coil-contact)

0.75mm amplitude at frequency of 10 to 55Hz (for 1 min) in each X, Y, Z direction for 10 min

Vibration (malfunction)

500 m/s² (≈ 50 G) in each X, Y, Z direction for 3 times

Shock

147 m/s² (≈ 15 G) in each X, Y, Z direction for 3 times

Shock (malfunction)-15 to 55 ℃, storage: -25 to 65 ℃ (no freezing or condensation)

Ambient temperature

35 to 85 %RH, storage: 35 to 85 %RH (no freezing or condensation)

Ambient humidity
Applicable wire- stranded■ DIN Rail• Mounting

1. Pull the Rail lock on the rear of the product to the direction ①.
2. Hang DIN rail hook on the rear of the product onto DIN rail.
3. Push the product to the direction ②, and push the Rail lock to the direction ③ to fix onto
the DIN rail.
DIN rail hook

Fork crimp terminal

≤16.0
≥4.1

≥3.0
≤5.9

Round crimp terminal

Replacing Relay

1. Disassemble a relay by using Two Way Ejector for relay replacement inside the product.
For TAKAMISAWA(Fujitsu)
relay

For MATSUSHITA[Two Way Ejector] (Panasonic) relay

Two Way
Ejectorlocation③• Removing
1. Insert a tool such as screwdriver into the hole of Rail lock.
2. Push the toll to the direction ① and pull the Rail lock.
3. Lift bottom of the product to the direction ② and remove the product from DIN rail.
①

A

24 VDCᜡ B

B

AA

A

A

A

A

GND C

B

CB

CB

CB

CC

B

C

B

C

412AAGND B

BA

B
CPin2018AC

16A

B

B

C

1412A

B

C

108619A

B

C

17AC

15A

BC

13BC

119750A 0B 0C 0D 0E0F
Upper 00 01 02 03 04 05 06 07 08 09
terminal R1+ R2+ R3+ R4+ R5+ R6+ R7+ R8+ R9+ R10+ R11+ R12+ R13+ R14+ R15+ R16+00 01 02 03 04 05 06 07 08 09
0A 0B 0C 0D 0E
0F
Low
terminal R1- R2- R3- R4- R5- R6- R7- R8- R9- R10- R11- R12- R13- R14- R15- R16-

• 32-point NPNController side (connector)
A A+24V +24V COM1
GND GND

Terminal sideA AB

CA A

A A

B

BB

A ACCOM2CA A

COM3A A

BCCA A

A A

A A

B

B

B

3836

34

32

01

-03

--02

-04

A A

A A

B

B

B

A A

A A

A A

B

C COM4CC• 32-point PNP

Controller side (connector)
1 3 2 4

■ PanelA A

GND GND COM1

Product with the mounting hole can be installed on panel with screw.
It is recommended to use M4×15 mm of spring washer screws.
If you use flat washer, its diameter should be Ø 6 mm.
Tighten the screw with the tightening torque of 0.7 to 1.0 N·m.

+24V +24V

Terminal sideACOM

7.62 mm Pitch Jumper BarBC

1. Using a nipper, cut the notches on the jumper bar as much as you need.
2. Loosen the screws which are needed to be common.
3. Insert the jumper bar under the loosen screws.
4. Tighten the screws.
7.62N[Inserting relay]

913Rail lock

2. After checking the location of the relay socket, insert the relay to be replaced.

[Disassembling relay using Two Way Ejector]

A

1 3 2 4②Rail lock

①Crimp Terminal Specifications
≤16.0
≥4.1

2

Terminal side②

• Unit: mm, Use the UL approved crimp terminal.

124 VDCᜡ C

0.5 to 0.6 N·m

≥3.0
≤5.9

78.8

78.8

Installation

AWG 22-16 (0.30 to 1.25 mm²)

Tightening torque43

DIN rail

0.75mm amplitude at frequency of 10 to 55Hz (for 1 min) in each X, Y, Z direction for 2 hours

Vibration

3Controller side (connector)

3,000 VACᜠ 50/60 Hz for 1 minute

RY1RY21014(-)
1• 16-point PNP

CASE: MPPO, BASE: PA66
(G25%), terminal pin: brassᜢ ᜨ ᜫ 06)

NPN / PNP model

RY311Controller side (connector)

Terminal side

CASE: MPPO, BASE: PA66(G25%), terminal pin: brass

NPN / PNP model

CASE, BASE: MPPO,terminal pin: brass

4-Ø4.535 mm DIN RAIL

-15(+)
5100

C

None

Input logic
Approval

10070

None

Power indicator: red,Power indicator: red,operating and disconnection operating and disconnection
indicator: blue
indicator: blue

Material

70

173

7.62 mm

Operation indicator: blueNone

C32-point

140

Screw

Indicator
VaristorB

16-point

40

16RY412(-)2(+)
6Terminal sideA

B16(-)
3(+)
7• 16-point NPN≤ 24 VDCᜡ ±10 %250 VACᜠ 3A,30 VDCᜡ 3A(-)
4(+)
8OUTPUTA

ABS-H16□-□

Controller side (connector)

INPUT

5.5

■ 16-point, 32-point

ABS-S04□-CNPower supply

2-Ø4.570
72❹ Input logic
C: COM None
N: NPN (+COM)
P: PNP (-COM)

38

32❸ Relay type
TN: TAKAMISAWA(Fujitsu) NYP
PA: MATSUSHITA(Panasonic) PA

Model

Applied relay 01)• 4-point

78.8

Specifications

N■ Wire connection

84

01. Fail-safe device must be installed when using the unit with machinery that may
cause serious injury or substantial economic loss.(e.g. nuclear power control,
medical equipment, ships, vehicles, railways, aircraft, combustion apparatus, safety
equipment, crime/disaster prevention devices, etc.)
Failure to follow this instruction may result in personal injury, economic loss or fire.
02. Do not use the unit in the place where flammable/explosive/corrosive gas, highhumidity, direct sunlight, radiant heat, vibration, impact or salinity may be present.
Failure to follow this instruction may result in explosion or fire.
03. Do not connect, repair, or inspect the unit, remove connector, or change Relay whileconnected to a power source.
Failure to follow this instruction may result in fire or electric shock.
04. Do not disassemble or modify the unit.
Failure to follow this instruction may result in fire or electric shock.

❹5.5

᜸ Warning Failure to follow instructions may result in serious injury or death.

-❷ Number of relay
04: 4-point
16: 16-point
32: 32-point

No. of connector pins• Observe all ‘Safety Considerations’ for safe and proper operation to avoid hazards.
• ᜸ symbol indicates caution due to special circumstances in which hazards may occur.

❸37

Safety Considerations• Instruction manual❷

2.7

3.2
9.5

Thank you for choosing our Autonics product.
Read and understand the instruction manual and manual thoroughly before using theproduct.
For your safety, read and follow the below safety considerations before using.
For your safety, read and follow the considerations written in the instruction manual,
other manuals and Autonics website.
Keep this instruction manual in a place where you can find easily.
The specifications, dimensions, etc. are subject to change without notice for productimprovement. Some models may be discontinued without notice.
Follow Autonics website for the latest information.

• Product❶❶ Connector type
S: Screw
H: Hirose connector

TCD210105AA

Product Components-■ 4-point• Unit: mm, For the detailed drawings, follow the Autonics website.

10.9

INSTRUCTION MANUAL

ABS

Wire Connection

35 mm DIN RAIL

This is only for reference, the actual product does not support all combinations.
For selecting the specified model, follow the Autonics website.

Dimensions

7270

ABS Series

Ordering Information

85.878.8Relay Terminal block (4/16/32-point)

0.8ACOM
B
CB

CC

Pin40

Upper
terminal--

R2Pin

39

37

Upper
terminal-COM00Low
terminal R1COM-

10Low
terminal R17-

COM2-

R335

11--

12R18-

C

COM1

R4-

33-

R531

COM313-

-

14-

R20

R19-

2805--

06-

29-

R727

15-

-

16-

R22

R21-

26
07

R8--

0A-

-

09-

0B--

R10--

19

R23-

Hirose (HIF3BA-20PA-2.54DSA)
1908

R9-

60.0

11818

820

20

17JB-7.62-08

222R24 R25N

• 20-pin connector

24-

Model

29.5C23■ Hirose connector pin arragement

4B

25

The number ofjumper pin

JB-7.62-04

BC

30R6C COM4COM3 BC

21-

R11-

19R1217-

-

1B

R27

R26-

140C-

-

0D

R13-

15COM41A-

16COM2-

C-

R14
131C-

-

1D-

R29

R28-

18, Bansong-ro 513Beon-gil, Haeundae-gu, Busan, Republic of Korea, 48002
www.autonics.com | +82-2-2048-1577 | sales@autonics.com

0E--

0F

R15R161E--

1F

R30-

40
39--

11R31Hirose (HIF3BA-40PA-2.54DSA)
110-• 40-pin connector
2129-R32