Bulletin 2CLM-2-5 Rev.:3/19/2012

Chemical Injection Technologies
Product/Specification Bulletin
SUPERIOR™ Gas Chlorinator Series CLM-2/5
200 PPD & 500 PPD - 5 Kg/hr & 10 Kg/HrFor Cylinder, Wall Manifold or Ton Container Mounting
GENERAL DESCRIPTIONThe SUPERIOR™ Series CLM-2/5 Gas Chlorinator is a state-of-the-art,vacuum-operated, solution feed type which mounts directly on achlorine valve. The chlorinator is mounted onto the chlorine valve ofa cylinder, wall manifold or ton container adaptor, using a very heavyduty, positive yoke clamp connection. A chlorine gas flow meter
indicates the amount of chlorine being fed. Chlorine flow rate is
manually adjusted and the design permits easy addition of a numberof automatic flow rate control devices. A high efficiency, water
operated ejector produces the vacuum necessary to operate thesystem. The ejector assembly contains a back-flow check valve
system to prevent pressurized waterfrom entering the chlorinator. A
spring-opposed diaphragm vacuum
regulator controls the chlorine gas
flow rate and also acts as the safety
shut-off valve.

FEATURESThe SUPERIOR™ Series CLM-2/5represents the most modern design
technology coupled with the very
best materials available to create anoutstanding, user friendly piece ofequipment. It is designed with user
safety as a primary concern.
1. A new ultra-thick, fluoroplastic
yoke coating gives SUPERIOR™
corrosion resistance, won't crack,peel or chip. Chlorine will not diffuse
through it to cause coating bubblingand peeling.
2. All molded parts are fiber-glass
reinforced ABS plastic, designed forSUPERIOR™ strength, warpresistance and chlorine resistance.
3. The rate valve "Seat" is purefluoroplastic and will not swell, stickor become brittle with age or
exposure to liquid chlorine.
4. All external bolts and nuts are
Titanium for complete corrosion
resistance..a SUPERIOR™ exclusive.
There are no stainless steel or monelnuts and bolts to corrode and freeze up in the presence of moist
chlorine gas.
5. Extra heavy-duty outlet threads on the ejector diffuser prevents
breakage from over-tightening or "bumping" of the ejector assembly.
6. The "Universal" ejector diffuser allows use of high pressure
solution hose, direct ejector mounting in mains, or in-line piping withrigid solution pipe, without special adaptors.
7. Easier to service and perform routine maintenance, with standard
size wrench lugs provided on all screwed-together ejector parts. No
more pipe wrenches to accidentally tear and scrape plastic surfaces.
8. All vacuum fitting holes are heavily reinforced to prevent thepossibility of cracking from over-tightening fittings.

10. Fewer parts, combined with SUPERIOR materials and aSUPERIOR design gives you a SUPERIOR™ Gas Chlorinator.

FLOW METER CAPACITIESA dual English/Metric scale variable area flow metering tube isprovided with a maximum capacity of 200 pounds per 24 hours 5Kg/Hr Model CLM-2) or 500 pounds per 24 hours - 10 Kg/Hr (ModelCLM-5). All metering tubes are interchangeable and may be changedin the field without special tools.

MODULAR DESIGNSUPERIOR™ Gas Chlorinators havebeen designed to give the maximum
flexibility in system installation. Thevacuum regulator and metering tube
panel are close coupled andmounted onto the chlorine cylinder
as a single assembly. The ejector
can be located wherever plumbing
and/or hydraulic conditions make itmost desirable. Modular design also
makes it easy and inexpensive toexpand or upgrade the system. The
metering tube panel may bedetached from the vacuum regulator
at any time, in just a few minutes, iffuture requirements or safety dictate
a remote metering application, or
multiple point chlorination is desired.

MATERIALSCONSTRUCTIONOF

One of SUPERIOR'S major
competitive advantages is the use of
the finest, strongest and mostdurable materials available.
Extensive use of Fluoroplastics andfiberglass reinforced thermoplastics
allow SUPERIOR™ Gas Chlorinators
to withstand attack by chlorine in any
form and to give the longest
operational life. Many parts areguaranteed for the life of the equipment against chlorine damage.

SYSTEM OPERATIONThe vacuum regulator is securely clamped onto the chlorine valve.
Water under pressure flows through the ejector at high velocity whichcauses a strong vacuum to be created. This opens the check valvesin the ejector assembly and transmits a vacuum signal through themeter tube/rate valve panel back to the vacuum regulator. When thevacuum reaches a pre-set level, the diaphragm in the regulator moves
to open the chlorine inlet safety valve, permitting gas to flow from thechlorine cylinder. The spring-opposed diaphragm and inlet valve
regulate the vacuum at this point.

Chlorine gas passes through the flow meter panel and rate control
9. "Dual-pressure" check valve is standard on all SUPERIOR™ gas
valve to the ejector. The gas mixes with the ejector water and isChlorinators. Proven high back-pressure unitized check valve design
protects against sudden surges up to 300 PSIG while a spring-loaded
discharged through the diffuser into the water being treated.
diaphragm check provides positive shutoff even when there is noback-pressure to force the seat closed.
Copyright © 2012, Chemical Injection Technologies, Inc.
Printed in U.S.A.

SPECIFICATIONSSTANDARD ACCESSORIESThe chlorinator shall be SUPERIOR™ MODEL CLM-2/5 manufactured
by Chemical Injection Technologies, Inc., Ft. Pierce, Florida, and shallhave a maximum capacity of _______ pounds per day (gr/hr)of
chlorine feed and shall be equipped with a chlorine flow meter of_______ pounds per day (gr/hr).

50 ft. - Vent & vacuum tubing
10 - Lead cylinder connection gaskets
1 - Vent insect screen

The chlorinator shall consist of a close-coupled vacuum
regulator/flow meter, and ejector/check valve. Each of theseassemblies shall be capable of being individually located whereversafety and/or operator convenience dictates.
The vacuum
regulator/flow meter assembly shall be capable of being separated
into independent vacuum regulator and metering panel assemblies
at any time for remote metering or multiple point chlorination
applications.

Inlet Water Assembly
Wall manifold kits
Booster pumps
Residual Analyzers
Automatic ControlsTon Container Adaptors

The vacuum regulator/flow meter shall mount directly on the chlorine
valve of a chlorine cylinder, wall manifold or ton container adaptor bymeans of a positive yoke type clamp having an integral tightening
screw with slide bar handle. No wrenches or other tools shall be
required to mount or dismount the vacuum regulator from thechlorine valve. The chlorine valve/chlorinator inlet adaptor shall be
constructed of corrosion-proof fluoroplastic material which shall beinert to the effects of wet, dry or liquid chlorine. The inlet safety shutoff/vacuum regulating valve shall be of capsulated design, easily
removable as a unit from the outlet side of the yoke. A fluoroplastic
filter shall be installed in the vacuum regulator inlet and shall becapable of removing impurities greater than 25 microns. A pressure
relief valve shall be incorporated into the vacuum regulator to prevent
pressure from building up in the system. All external screws and nuts
shall be made of Titanium to prevent corrosion.
The vacuum regulator/flow meter bodies shall be constructed offiberglass reinforced thermoplastic material and shall incorporate aflow rate control valve made of fluoroplastic material which is inert tothe corrosive effects of chlorine.The rate valve metering tip shall be
constructed of metal which is completely impervious to the effects ofwet, dry or liquid chlorine attack. Design shall provide for full closingof the rate valve without engaging the control surfaces,
to prevent
damage. . Minimum calibrated feed rate shall be 1/20th of maximum
flow meter scale (20:1 turndown ratio). Accuracy shall be ±2% ofmaximum.
Vacuum shall be created by a fixed-throat venturi/ejector system
connected directly to the chlorine solution diffuser. A dual highpressure/low-pressure check valve system shall prevent water fromentering the gas system. The ejector assembly shall be capable ofwithstanding water pressure up to 300 PSIG (20.7 Bars). A universaltype chlorine solution diffuser shall be provided which shall allow
close-coupling of the ejector to a water main, use of flexible solution
hose or rigid solution pipe without the use of special adaptors.

OPTIONAL ACCESSORIES AVAILABLE
Gas Masks
Gas Detectors
ScalesGaugesChlorine Comparators
Others Available

OTHER SUPERIOR™ SYSTEMS AVAILABLE
AUTOMATIC SWITCHOVER GAS CHLORINATORSMULTIPLE-POINT GAS CHLORINATORS
100 POUNDS PER DAY (2000 GR/HR)
500 POUNDS PER DAY (10 KG/HR)GAS SULFONATORS (DECHLORINATOR)AMMONIATORSAUTOMATIC FLOW PROPORTIONING
AUTOMATIC RESIDUAL CONTROL____________________________________________

Chemical Injection Technologies, Inc.
835 Edwards Rd., Ft. Pierce, FL, 34982, USA(772) 461-0666
Fax: (772) 460-1847
E-Mail: superior@chlorinators.com
www.chlorinators.com____________________________________________