Specification CL-1016/2016 Rev.:4/11/2010

Chemical Injection Technologies
Product/Specification Bulletin
SUPERIOR™ Automatic Switchover Gas Chlorinator
Series CL-1016/2016, 1000 PPD & 2000 PPD - 20 Kg/Hr & 40 Kg/HrHigh Capacity
GENERAL DESCRIPTIONThe SUPERIOR™ Series CL-1016/2016 Automatic Switchover Gas
Chlorinator is a state-of-the-art, vacuum-operated system designed
to automatically switch chlorine feed from an empty chlorine source
to a full source. The Series CL-1016/2016 allows round-the-clockchlorination without being concerned about running out of chlorine
when the system is unattended. Series CL-1016/2016 chlorinators areof the vacuum-operated solution feed type designed to mount directlyon the auxiliary valve of a wall manifold, for high chlorine gas feed
rates up to 2000 pounds per 24 hours (40 Kg/hr). Two vacuum
regulators, each containing an integral and independent latchingmechanism, are mounted directly onto two chlorine manifold auxiliaryvalves. A chlorine gas flow meter panel indicates the amount ofchlorine being fed and may be located wherever it is safest and mostconvenient. Chlorine flow rate is manually adjusted and the designpermits easy addition of a number of automatic flow rate control
devices. A high efficiency, water operated ejector produces thevacuum necessary to operate the system. The ejector assembly
contains a back-flow check valve system to prevent pressurized waterfrom entering the chlorinator. A spring-opposed diaphragm vacuum
regulator controls the chlorine gas flow rate and also acts as thesafety shut-off valve.

FEATURESThe SUPERIOR™ Series CL-1016/2016 represents the most modern
design technology coupled with the very best materials available tocreate an outstanding, user friendly piece of equipment. It is
designed with user safety as a primary concern.
1. A new ultra-thick, fluoroplastic yoke coating gives superior
corrosion resistance, won't crack, peel or chip. Chlorine will not
diffuse through it to cause coating bubbling and peeling
2. All molded parts are fiber-glass reinforced ABS plastic, designed
for superior strength, warp-resistance and chlorine resistance.
3. All external bolts and nuts are Titanium for complete corrosion
resistance..a SUPERIOR™ exclusive.
4. All vacuum fitting holes are heavily reinforced to prevent thepossibility of cracking from over-tightening fittings.
5. “Y-Check” check valve design offers very low cracking pressureand virtually no pressure drop due to friction. Check valves arecomplete modules and can be close-coupled to the ejector or locatedanywhere in the vacuum piping system for maximum flexibility.
6. Built-in switchover "detent" mechanism in each regulator requires
no field adjustment, and allows operator to easily designate thestandby and operating cylinders.
7. “Capsule” type inlet safety valve design allows easy removal for
inspection or cleaning, using no special tools.
8. All-vacuum operation, combined with modular design of the major
operating components, allows pressurized chlorine gas to be isolated
from the operating areas for greater safety.

Pub: CL-1016/2016, Rev: 11042010

9. All SUPERIOR™ gas chlorinators carry a 3-year limited warranty,
in addition to a lifetime warranty on 4 vital parts: main diaphragm,springs, inlet adaptor and body bolts.
10. Fewer parts, combined with SUPERIOR™ materials and aSUPERIOR™ design gives you a superior gas chlorinator.

FLOW METER CAPACITIESSUPERIOR™'s modular design concept allows the chlorine gas
indicating meter and flow rate control valve to be located wherever it
is most convenient for the operator, and also in the safest location.
A dual English/Metric scale variable area flow metering tube isprovided with a maximum capacity of 1000 pounds per 24 hours - 20Kg/hr (Model CL-1016) or 2000 pounds per 24 hours - 40 Kg/hr(Model CL-2016). All metering tubes are interchangeable and may bechanged in the field without special tools.

MATERIALS OF CONSTRUCTION
One of SUPERIOR's major competitive advantages is the use of thefinest, strongest and most durable materials available. Extensive useof Fluoroplastics and fiberglass reinforced thermo-plastics allow
SUPERIOR™ Gas Chlorinators to withstand attack by chlorine in any
form and to give the longer operational life. Many parts areguaranteed for the life of the equipment against chlorine damage.

SYSTEM OPERATION
The automatic switchover vacuum regulators are securely clamped
onto the auxiliary chlorine valves of wall manifolds. Vacuum piping
connects each regulator to a junction point. A single piece of vacuum
piping connects the junction to the wall mounted remote metertube/rate valve panel. The ejector is connected to the remote meter
panel with a single piece of vacuum tubing. A wall mounted pressure
relief/vent valve is connected by a piece of vacuum tubing to thejunction point.
Water under pressure flows through the ejector at high velocity
causing a strong vacuum to be created. This opens the check valve
in the ejector assembly and transmits a vacuum signal through theremote meter tube/rate valve panel, back to the vacuum regulators.
When the vacuum reaches a pre-set level, the diaphragm in theregulator moves, opening the chlorine inlet safety valve, and permits
gas to flow from the chlorine cylinder. The spring-opposed
diaphragm and inlet valve regulate the vacuum at this point.
Chlorine gas passes through the regulator, junction point, remoteflow meter panel and rate control valve to the ejector. The gas mixes
with the ejector water and is discharged through the diffuser into thewater being treated.
When the chlorine supply is depleted in one source, vacuum starts toincrease in the system. This causes the diaphragm in the "stand-by"
regulator to be pulled back, overcoming the detent mechanism andopening the inlet/safety valve. Chlorine gas is then withdrawn fromthe "stand-by" cylinder to satisfy the increased system vacuum andthe vacuum returns to the operating level. The empty chlorine
source(s) is replaced at the operator's convenience, and the regulator
then placed on "stand-by".

Copyright© 1997, Chemical Injection Technologies, Inc.

Printed in U.S.A.

SPECIFICATIONS

The chlorinator shall be SUPERIOR™ MODEL CL___(1016/2016) manufactured by Chemical Injection
Technologies, Inc., Ft. Pierce, Florida, and shall have amaximum capacity of _______ pounds per day (kg/hr)of
chlorine feed and shall be equipped with a chlorine flow meterof _______ pounds per day (gr/hr).
The chlorinator shall be of modular design consisting of two(2) automatic switchover vacuum regulators, one (1) pressure
relief/vent valve, one (1) flow meter/rate valve panel, and one(1) ejector/check valve. Each of these assemblies shall becapable of being individually located wherever safety and/oroperator convenience dictates.
The vacuum regulators shall mount directly on the auxiliary
chlorine valves of wall manifolds by means of a positive yoketype clamp having an integral tightening screw with slide barhandle. No wrenches or other tools shall be required tomount or dismount the vacuum regulator from the chlorinevalve. The chlorine valve/chlorinator inlet adaptor shall be
constructed of corrosion-proof fluoroplastic material whichshall be inert to the effects of wet, dry or liquid chlorine. The
inlet safety shut-off/vacuum regulating valve shall be ofcapsulated design, easily removable as a unit from the outletside of the yoke. All external screws and nuts shall be madeof Titanium to prevent corrosion.
Each automatic switchover vacuum regulator shall contain it's
own built-in diaphragm detent mechanism, which shall bemade entirely of non-metallic corrosion resistant materials.
The detent mechanism shall be factory pre-set and shall not
require any field adjustment.
The flow meter/rate control valve panel shall be capable ofmounting wherever it is safest and most convenient foroperating personnel. The panel shall be constructed ofchlorine resistant thermoplastic material and shall incorporate
a flow rate control valve made of fluoroplastic material whichis inert to the corrosive effects of chlorine. The rate valve
metering tip shall be constructed of fine, hard-drawn silver.
Design shall provide for full closing of the rate valve without
engaging the control surfaces, to prevent damage.
Vacuum shall be created by a fixed-throat venturi/ejector
system. A spring loaded “Y” type check valve system shallprevent water from entering the gas system. The ejector
assembly shall be capable of withstanding water pressure up
to 150 PSIG (10.2 Bars)

STANDARD ACCESSORIES (Included with chlorinator)
2- Remote vacuum regulators

25 ft. -d" Vent tubing

1- Remote metering panelgaskets
1- Remote Ejector assembly
1- Check Valve assembly
1- Pressure relief/vent valve

20 - Lead cylinder
1 - Cylinder Wrench
1 - Vent insect screen

OPTIONAL ACCESSORIES AVAILABLE
Inlet Water Assembly
Wall manifold kits
Booster pumps
Residual Analyzers
Automatic Controls
Ton Container Adaptors

Gas Masks
Gas Detectors
ScalesGaugesChlorine Comparators
Others Available

OTHER SUPERIOR™ SYSTEMS AVAILABLE
MULTIPLE-POINT GAS CHLORINATORS

100 POUNDS PER DAY (2000 GR/HR)
200 POUNDS PER DAY (5 Kg/hr)
500 POUNDS PER DAY (10 Kg/hr)
GAS SULFONATORS (DECHLORINATOR)AMMONIATORSAUTOMATIC FLOW PROPORTIONING
AUTOMATIC RESIDUAL CONTROL____________________________________________

Chemical Injection Technologies, Inc.
835 Edwards Rd., FL, 34982, USA(772) 461-0666
Fax: (772) 460-1847
E-Mail: superior@chlorinators.com
www.chlorinators.com__________________________________