Luminous SkyCeilings

Infinity EcoPlus LED

CONFORMS TO:
ANSI/UL STD 1598
IEC 60598-2-2, 60598-1,62471 AND 62031
EN 60598-2-2 AND 50598-1
CERTIFIED TO:
CAN/CSA STD C22.2 No. 250.0™

4010304

Specifications
1234

Lighting (EcoPlus LED back lit light box):
Color temperature: 6500K
Strict LED binning standards assure consistent & high quality illumination
State of the art back lit technologies provide uniform illumination
for the Luminous SkyTile graphic
Housed in a white powder-coated, extruded (non-ferrous) aluminum frameMoisture and chemical resistant
Each fixture has a four knock-out junction box

Infinity EcoPlus

EP-CIR-INF-4, -6, -9, -12
Ceiling Grid Mount
Back Illuminated Sky Image Ceiling

Luminous SkyTile (lens):
Acrylic, Acrylite, or polycarbonate substrate
Lightweight & durable
High resolution reproduction from proprietary digital image file
Color-calibrated for daylight quality light source
Non-glare matte finish
Fade resistant pigmented inks containing UV inhibitors
Manufactured to fit Luminous SkyTile Classic Elevator

123

Classic Elevator (frame):
Moisture resistant, light weight aluminum1.25” (31.8mm) vertical profile
Quick and easy installation
Powder coated, white matte finish to match standard gridCompatible with standard 15/16” grid systems
Precision machined corners, seamless architectural appearance

4Perimeter and Grid:
Classic white aluminum perimeter with 8” vertical profile
Standard 15/16” white ceiling grid
Suspension system package
Pre-cut to four standard diameters: 4’ 3 1/8”; 6’ 7 1/2”; 9’ 1” ; 12’ 8 1/2”
UL, CSA, and CE Certified:
EP and EPCST Series when used with 24PS HLG Power System,
UL Listed or CE Compliant power supply fully certified by Intertek Group plc

Fixtures, pre-cut ceiling grid and perimeter

Dimensions and Weights

Electrical:
24V DC, Amps and Watts varies per SkyCeiling:
INF-4 @ 3.4A, 80.5W
INF-6 @ 8.0A, 190W
INF-9 @ 14.7A, 351W
INF-12 @ 29.0A, 696W
Sky Factory 24PS HLG Power System
Converts 100-240V AC (277V AC North America only) to 24V DC
Size and quantity per installation calculated by Sky Factory
Power system aluminum enclosure
Mounted on baseplate with junction box on input and output ends
See 24PS HLG Power System Technical Specifications sheet
Sky Factory provided HLG dimmable power supply (International Only)
Converts 100-240V AC (277V AC North America only) to 24V DC
Client provided UL Listed or CE Compliant power supply
Must convert V AC to 24V DC
Items not provided:
AC wiring between fuse/breaker panel and 24V DC power system
Dimmer wiring between 24V DC power system and switch/dimmer control box
DC wiring between 24V DC power system and Infinity EcoPlus
DC wiring between EcoPlus light boxes

All SkyCeilings 8” (20.3cm) deepINF-4:
4’ 3 1/8” (129.9cm) diameter
52 lbs (23.6kg);• 13lbs (5.9kg) per suspension pt

See Infinity w /EcoPlus Installation Instructions; andCustom EcoPlus Electrical Packet (24PS HLG), Electrical Instructions (HLG) or
Electrical Instructions (Fixture Only)

INF-6:
6’ 7 1/2” (202cm) diameter
123 lbs (55.8kg);• 31lbs (14kg) per suspension pt

Installation:
Elevators, tiles and luminaires easily installed into standard 15/16” grid andperimeter system provided.
Infinity EcoPlus SkyCeilings are designed to be suspended from a ceilingin a variety of combinations and configurations.

INF-9:
9’ 1” (277cm) diameter
232 lbs (105.3kg);• 39lbs (17.6kg) per suspension pt

Infinity EcoPlus SkyCeilings are not MRI compatible

INF-12:
12’ 8 1/2” (387.5cm) diameter
308 lbs (139.8kg);• 26lbs (11.7kg) per suspension pt

Restraint, seismic bracing not provided
For recommendations, see Infinity w/ EcoPlus Installation Instructions, Appendix A.
US Patent Information:
Our products, systems, and methods may be protected by one or more of the following US Patents:
Pat. 9,164,011, Pat. 8,851,700, Pat. 7,959,316, and Pat. 7,481,550, as well as other patents pending.

641.472.1747

Information may be subject to change without notice

9.28.2020