Sky Factorylooser kerning

Sky FactoryTMwww.skyfactory.com•

toll free 1.866.759.3228

Custom EcoPlus Electrical Instructions(24PS HLG)

Junction Box
Black wire is negative
Red wire is positive
24 volt DC

24PS HLG
Power System

Installation Packet Includes:
Custom EcoPlus Electrical Instructions (24PS HLG)
EL001250 - Without Dimmer
EL001450 - With Lutron Dimmers
EL001449 - With Jung Dimmers
EL001455 - Lutron Dimmers with Multiple Power Systems
EL001447 - Jung Dimmers with Multiple Power Systems
Electrical Layout EL1 & EL2
Sky Factory 24PS HLG Power System Installation
For technical support at any time during the installation, please call us toll free at 866-759-3228.
We want your installation to go as smoothly as possible. Thank you for choosing Sky Factory.

6/7/2021

Custom EcoPlus electrical requirements:
All EcoPlus fixtures are 24V DC only.
EcoPlus fixtures must be mounted in dry locations only.
EcoPlus fixtures must be powered by provided UL, CSA and CE Compliant 24PS HLG Power System
Sky Factory 24PS HLG Power System:
Input (Typ): 90-305V, 47 - 63 Hz
Output: 24V DC
Maximum Watts (useable) per power system: 600 Watts
Available sizes: 40W, 60W, 80W, 100W, 120W, 150W, 185W, 240W, 320W, 480W, 600W
Power System aluminum enclosure
Mounted on baseplate with junction box on input and output ends
For mounting dimensions and weights, see “Sky Factory 24PS HLG Power System Installation”
For power system wire sizes, see “Sky Factory 24PS HLG Power System Installation”
Power system must have 2” clearance for air flow. Wall mount recommended.
Power system must be mounted in dry locations.
For installation specific number of power systems and number of fixtures per power system,
see Electrical Layout EL1 & EL2
For EcoPlus with 24PS HLG Power System general wiring diagrams, see
EL001250, EL001449 & EL001450
For single dimmer control and multiple power systems, see
EL001447 & EL001455
RF filter, if used, is not provided by Sky Factory. One filter per power system required.

Sky Factory

Page 2Custom EcoPlus electrical requirements (cont’d):Sky Factory provided dimmer control (where specified):
Lutron Diva DVSTV 0 - 10V dimmer/switch (UL & CSA compliant)
Input: auto-ranging 120 - 277V AC
Lutron Diva DVTV 0 - 10V dimmer/switch and PP-DV power pack (UL & CSA compliant)
Input: auto-ranging 120 - 277V AC
Lutron Diva mounts in standard single-gang electrical box
White standard, other colors available on request
Jung 240-10 dimmer/switch and external relay where specified (CE compliant)
Input: 230 - 240V AC
Installs in appliance box to DIN 49073
For dimming requirements, see page 5.
For dimmer wiring diagrams, see dimmer control (and relay where specified) andwiring diagrams included
For other dimmer controls provided, see installation specific EL2 included
Electrical work must be performed by a qualified electrician who is familiar with DC lighting systems
and must conform to all local and national codes.

Non-Dimmable and Dimmable Certification:
ES22 Series, ES24 Series, ES26 Series, ES33 Series, ES34 Series, ES36 Series, ES44 Series, ES46 Series, ESCST Series,
EP22 Series, EP24 Series, EP26 Series, EP33 Series, EP34 Series, EP36 Series, EP44 Series, EP46 and EPCST Series fixtures
when used with 24PS HLG Power System UL, CSA and CE Listed by Intertek Group plc
Sky Factory

Page 3Step 1: Wiring the EcoPlus fixtures to the power system
See also wiring diagrams on pages 6-10 and Electrical Layout EL1 & EL2

Notice: The LED fixtures are 24V DC ONLY.
AC voltage connected directly to the fixtures
will destroy the lighting system.

Fixtures are wired together in single or multiple circuits.
Each circuit is dedicated to a single power system and may be arranged in rows or clusters, depending on installation.
For installation specific number of fixtures per power system, see Electrical Layout EL2
A junction box with 1/2” trade size knock-outs is attached on top corner of each fixture.
•Power leads inside fixture junction box are polarized, red (+) and black (-).

•Wire size 18 AWG stranded.

•NOTE: Where a fixture has multiple junction boxes, each junction box will be included in a separate circuit.

Wiring from fixtures to V DC side of provided power system is polarized, positive (+) to positive (+)
and negative (-) to negative (-):
EcoPlus fixture red “+” to power system Vo+
EcoPlus fixture black “–” to power system Vo–
For power system V DC wire sizes, see EL001250
HLG-480H-24B and HLG-600H-24B have two sets of ouput leads. Meanwell recommends loading no more than:
240 Watts on each set of cables for HLG-480H-24B
480 Watts on each set of cables for HLG-600H-24B
Wire and additional junction boxes from the fixtures to the power system supplied by others.
Wire gauge must conform to local and national codes. Voltage drop of no more than 2% is recommended.

Sky Factory

Page 4

Step 2: Wiring the power system to source V AC
Run power to V AC side of the power system. For power system V AC wire size,see “Sky Factory 24PS HLG Power System Installation”
Load to power system ACL
Neutral to power system ACN
Ground to power system(GREEN/YELLOW)

Wire gauge must conform to local and national codes.
Install the power switch on the V AC input side of the power system.

Step 3: Dimming requirements
Contact the Sky Factory if you plan on using a dimming system provided by others.

Notice: Dimming using non-approved systems

may permanently damage LED’s and will void the warranty!

Wiring a Sky Factory provided dimmer control:
To wire the dimmer control (and external relay where specified), refer to wiring diagram included
with dimmer and relay and wiring diagrams included.

Step 4: Checking the polarity
Notice: CHECK THE POLARITY BEFORE TURNING ON POWER. MAKE SURE:
Red wires on the fixtures go to the “+” terminals of the power supply
Black wires on the fixtures go to the “–” terminals of the power supply
IF THE SYSTEM IS WIRED BACKWARD, IT WILL DESTROY THE LED’S!
Sky Factory

Page 5

Sky Factory

Page 6

Sky Factory

Page 7

Sky Factory

Page 8

Sky Factory

Page 9

Sky Factory

Page 10