looser kerning

Sky FactoryTMwww.skyfactory.com•

toll free 1.866.759.3228

Revelation w/ EcoPlus Electrical Instructions(HLG)

Junction Box
Black wire is negative
Red wire is positive
24 volt DC

Power Supply

Installation Instructions includes:
Revelation w/ EcoPlus Electrical Instructions (HLG)
Wiring Diagram EL001391, EL001428 & EL001453
Installation specific wiring diagram (where applicable)

For technical support at any time during the installation, please call us toll free at 866-759-3228.
We want your installation to go as smoothly as possible. Thank you for choosing Sky Factory.
3/23/2022

Revelation w/ EcoPlus Electrical Requirements:
EP24 Series = EP24, EP26M, EP24G 		
EP34 Series = EP34, EP34M, EP34G		
EP46 Series = EP46, EP46M, EP46G

EP26 Series = EP26, EP26M, EP26G		
EP36 Series = EP36, EP36M, EP36G		

EP33 Series = EP33, EP33M, EP33G
EP44 Series = EP44, EP44M, EP44GNOTE: For custom sizes, see installation specific wiring diagram included (where applicable)
All EcoPlus fixtures are 24V DC only.
EcoPlus fixtures must be powered only by provided UL Recognized, CE Compliant 24V DC power supplyDry locations only.
For installations with multiple power supplies, see
installation specific wiring diagram included (where applicable)
For installations with one or more custom sizes, see
installation specific wiring diagram included (where applicable)
RF filter, if used, is not provided by Sky Factory.

Sky Factory provided external dimmable power supply:
Input (Typ) 90-305V, 47 - 63 Hz
Output 24V DC
UL (U.S. and Canada) Recognized and CE Compliant
Maximum Watts (useable) per power supply: 600 Watts
Available sizes: 40W, 60W, 80W, 100W, 120W, 150W, 185W, 240W, 320W, 480W, 600W
AC input wire sizes: 17 AWG on 40-600W
DC output wire sizes: 17 AWG on 40-240W,480W; 14 AWG on 320W,600W
Dimmer wire sizes: 20 AWG on 40-480W; 18 AWG on 600W

Power supply must have 2” clearance for air flow. Wall mount recommended.
Power supply must be mounted in dry locations.
Surface mountable
Sky Factory

Page 2

Revelation w/ EcoPlus Electrical Requirements (cont’d):Sky Factory provided dimmer control (where specified):
Lutron Diva DVSTV 0 - 10V dimmer/switch (UL & CSA compliant)
Input: auto-ranging 120 - 277V AC
Mounts in standard single-gang electrical box
White standard, other colors available on request
Lutron Diva DVTV 0 - 10V dimmer/switch and PP-DV power pack (UL & CSA compliant)
Input: auto-ranging 120 - 277V AC
Lutron Diva mounts in standard single-gang electrical box
White standard, other colors available on request
Jung 240-10 dimmer/switch and external relay where specified (CE compliant)
Input: 230 - 240V AC
Installs in appliance box to DIN 49073
Helvar TK4 140 dimmer/switch (CE compliant)
Input: 220 - 240V AC
Mounts in standard UK or DIN back box
For dimming requirements, see page 6
For dimmer wiring diagrams, see dimmer control (and relay where specified) andwiring diagrams included
Electrical work must be performed by a qualified electrician who is familiar with DC lighting systems
and must conform to all local and national codes.

Non-Dimmable and Dimmable Certification:
ES22 Series, ES24 Series, ES26 Series, ES33 Series, ES34 Series, ES36 Series, ES44 Series, ES46 Series, ESCST Series,
EP22 Series, EP24 Series, EP26 Series, EP33 Series, EP34 Series, EP36 Series, EP44 Series, EP46 and EPCST Series fixtures
when used with 24PS HLG Power System UL, CSA and CE Listed by Intertek Group plc
Sky Factory

Page 3

Step 1: Wiring the Revelation fixtures to the power supply
See wiring diagrams on pages 7-9 and installation specific wiring diagram included (where applicable)

EcoPlus Lighting System - EP24 to EP46 Series
TSF Model No.

Light Box Dimensions and Weight Only

System Wattage Input Current(Max)@ 24 Volts DC

WxLxH

WeightEP24

22.8125 x 46.8125 x 5.85 (inches)

10.2 lb

47.1

1.96A

EP26

22.8125 x 70.8125 x 5.85 (inches)

16.7 lb

69.12.88A

EP33

34.8125 x 34.8125 x 5.85 (inches)

12.6 lb

51.8

2.16A

EP34

34.8125 x 46.8125 x 5.85 (inches)

15.9 lb

69.1

2.88A

EP36

34.8125 x 70.8125 x 5.85 (inches)

22.4 lb

103.7

4.32A

EP44

46.8125 x 46.8125 x 5.85 (inches)

19.9 lb

92.2

3.84A

EP46

46.8125 x 70.8125 x 5.85 (inches)

27.8 lb

138

5.75A

EP24M

57 x 117 x 14.86 (cm)

4.5 kg

47.1

1.96A

EP26M

57 x 177 x 14.86 (cm)

7.4 kg

69.1

2.88A

EP33M

87 x 87 x 14.86 (cm)

5.6 kg

51.8

2.16A

EP34M

87 x 117 x 14.86 (cm)

7.2 kg

69.1

2.88A

EP36M

87 x 177 x 14.86 (cm)9.9 kg

103.7

4.32A

EP44M

117 x 117 x 14.86 (cm)

8.8 kg

92.2

3.84A

EP46M

117 x 177 x 14.86 (cm)12.3 kg

138

5.75A

EP24G

59.5 x 122 x 14.86 (cm)4.8 kg

47.1

1.96A

EP26G

59.5 x 184.5 x 14.86 (cm)7.9 kg

69.1

2.88A

EP33G

90.8 x 90.8 x 14.86 (cm)5.9 kg

51.8

2.16A

EP34G

90.8 x 122 x 14.86 (cm)

7.5 kg

69.1

2.88A

EP36G

90.8 x 184.5 x 14.86 (cm)10.6 kg

103.7

4.32A

EP44G

122 x 122 x 14.86 (cm)9.4 kg

92.2

3.84A

EP46G

122 x 184.5 x 14.86 (cm)13.1 kg

1385.75A

NOTE: For custom sizes, see also installation specific wiring diagram included (where applicable)

Notice: The LED fixtures are 24V DC ONLY.
AC voltage connected directly to the fixtures
will destroy the lighting system.

Sky Factory

Page 4

Step 1 continued
Fixtures are wired together in single or multiple circuits.
Each circuit is dedicated to a single power system and may be arranged in rows or clusters, depending on installation.
A junction box with 1/2” trade size knock-outs is attached on top corner of each fixture.
•Power leads inside fixture junction box are polarized, red (+) and black (-).

•EP36, -44, -46 & ES36 -44-, -46 have two sets of leads and will be wired together red (+) to red (+) and black (-) to black (-).

•Fixture wire size 18 AWG stranded.

Wiring from fixtures to V DC side of provided power supply is polarized, positive (+) to positive (+)
and negative (–) to negative (–):
EcoPlus fixture red “+” to power supply Vo+
EcoPlus fixture black “–” to power supply Vo–
For power supply V DC wire size, see wiring diagrams included
HLG-480H-24B and HLG-600H-24B have two sets of ouput leads. Meanwell recommends loading no more than:
240 Watts on each set of cables for HLG-480H-24B
480 Watts on each set of cables for HLG-600H-24B
Wire and additional junction boxes from the fixtures to the power supply provided by others.
Wire gauge must conform to local and national codes. Voltage drop of no more than 2% is recommended.

Step 2: Wiring the power supply to source V AC
Run power to V AC side of the power supply.
Load to power supply ACL
Neutral to power supply ACN
Ground to power supply(GREEN/YELLOW)

Wire gauge must conform to local and national codes.
Install the power switch on the V AC input side of the power supply.

Sky Factory

Page 5

Step 3: Dimming requirements
Contact the Sky Factory if you plan on using a dimming system provided by others.

Notice: Dimming using non-approved systems

may permanently damage LED’s and will void the warranty!

Wiring a Sky Factory provided dimmer control:
To wire the 0-10V dimmer control (and external relay where specified), refer to wiring diagram included
with dimmer and relay and wiring diagrams included.

Step 4: Checking the polarity

Notice: CHECK THE POLARITY BEFORE TURNING ON POWER. MAKE SURE:
Red wires on the fixtures go to the “+” terminals of the power supply
Black wires on the fixtures go to the “–” terminals of the power supply
IF THE SYSTEM IS WIRED BACKWARD, IT WILL DESTROY THE LED’S!

Sky FactoryPage 6

Sky Factory

Page 7

Sky Factory

Page 8

Sky Factory

Page 9