INFORMATION NOTE
Date: 10 March 2022

Situation at the Chernobyl site

On 9 March at 11.22am, the Ukrainian nuclear safety authority SNRIU informed IAEA that the external power
supplies of the Chernobyl plant facilities had been cut off. The site's emergency generators would be supplying
power to the facilities, with enough fuel for 48 hours.
IRSN presents below an assessment of the risks associated with the loss of external power supplies for the site’svarious facilities, including the loss of emergency power supply, which is a potential situation that could comeabout rapidly if power is not restored to the site because the generator fuel reserves run out.

Reactors
Reactors 1, 2 and 3 at the Chernobyl site have been shut down for over 20 years. All the fuel assemblies of thesereactors have been transferred to the site's storage facility (see below). There is no risk of releases from thesefacilities, which are not backed up by diesel generators.
Reactor 4, which was damaged in 1986, was initially covered by a temporary sarcophagus as an emergency
measure. Uncertainties concerning the structural resistance of this sarcophagus led to the construction of acontainment structure (NSC for New Safe Confinement), which was completed in 2017 (250 m wide, 160 m long,100 m high). The temporary sarcophagus is being dismantled. The NSC ventilation system is backed up by two
dedicated generators. In the event of total loss of electrical power, facility containment will be provided solely
by the static containment of the structure. The dismantling of the sarcophagus of the damaged reactor has
probably been suspended due to the conflict, so this containment should be sufficient to prevent releases intothe environment.

Spent fuel storage facility
The facility consists of a storage pool (ISF-1) with approximately 20,000 assemblies and a dry storage facility (ISF2). Spent fuel elements are gradually transferred from the pool to ISF-2.
 Underwater storage pool ISF 1
The safety systems of this facility are backed up by two diesel generators with fuel reserves to last 48 hours.
The studies carried out after the accident at the Fukushima Daiichi plant on the consequences of total loss of thepool cooling systems indicate a slow rise in pool water temperature to a temperature of around 60°C but nodewatering of the assemblies and therefore no radioactive releases into the environment.

1/2

INFORMATION NOTE - SITUATION AT THE CHERNOBYL SITE - 09/03/2022

ISF 2 dry storage facility

To date, about 2,000 assemblies have been transferred from ISF-1 to ISF-2.
This facility does not present a risk in the event of total loss of electrical power, as the power removal from thefuel assemblies is completely passive.

Loss of the facility’s control systems
Although the loss of power at the Chernobyl site does not have consequences that could lead to environmental
releases, it does imply the loss of the facility's command-control systems. Thus, all the technical data used by thesite’s real-time monitoring (water level, temperature, radioactivity, etc.) and alarm systems will cease to beavailable; this could delay the reactions of personnel if an incident occurs on the facility. The loss of power would
also mean the loss of lighting, heating and certain communication systems, resulting in deteriorated working
conditions for personnel, who are already suffering from the stress of the current situation.

2/2