Luminous Virtual Window
4010304

CONFORMS TO:
AC – ANSI/UL STD 1598
IEC 60598-2-1,60598-2-2,60598-1
DC – ANSI/UL STD 2108
IEC 60598-2-1,60598-2-2,60598-1
CERTIFIED TO:
CAN/CSA STD C22.2 No. 250.0

Specifications™

LVW LED Edge-Lit

1

Light Box:6063 T6 extruded aluminum case with clear anodized finish
LED edge-lit daylight quality light source
Designed for easy access to electrical components
Precision machined assembly

2Luminous Image Panel:
Acrylic, Acrylite, or polycarbonate substrate
Lightweight & durable
High resolution reproduction from proprietary digital image file
Color-calibrated for daylight quality light source
Fade resistant pigmented inks containing UV inhibitors
Easy access for installation and cleaning

3Trim:
Wide range of styles in woods and aluminum
Quick and easy installation
Safety catch hardware included

Recessed or Surface Mount
Wall Image Display

UL, CSA, and CE Certified:
LV5-2240 - LV5-4872 V AC fully certified by Intertek Group plc
LV5-2240 - LV5-4872 V DC fully certified by Intertek Group plc
Electrical (see table for variants):
V AC Luminous Virtual Window for non-MRI applications
Internal power supply hardwired inside fixture
Input 100-277V AC, 0.6A max. at 115V AC, 50/60Hz
V DC Luminous Virtual Window for MRI applications
External power supply remotely located (see details below)
Power consumption of V AC and V DC Luminous Virtual Windows(see table on page 2)
Terminal block wire range #12-22 Awg (DC Model only)
Wiring access hole limited to 1/2” nominal trade size conduit
Min 90°C supply connectors/Les fils d’alimentation 90°C Min
Internal power supply (V AC Luminous Virtual Window only):
Power factor: 0.92; supply current: 0.6A
External power supply (V DC Luminous Virtual Window only):
Input (Typ) 100-240V AC/277V AC, 0.85A/0.40A, 50-60 Hz(277V AC for North America only)
Output 24V DC, 3.4A
Class 2, UL8750 Listed (U.S. and Canada) and CE Compliant
Power factor: 0.96; supply current: 0.85A
Surface mountable, suitable for dry/damp/wet locations
Junction box wiring access holes limited to 1/2” nominal trade size conduit
Shielded Environments: RF filters supplied by shielding provider
102 - 258 high-efficiency white LEDs per unit (Not intended as a light source)
Daylight quality light temperature – cool daylight
80,000 hour rated life (80% @ 40,000 hrs.)
Environment:
Operating temperature:
V AC Luminous Virtual Window ta: 50°C max
V DC Luminous Virtual Window ta: 50°C max
External Power Supply ta: 50°C max
Storage temperature:
V AC Luminous Virtual Window: ―40°C~+85°C
V DC Luminous Virtual Window: ―40°C~+85°C
External Power Supply: ―40°C~+80°C
Indoor use only: dry applications only/endroits
secs seulement
Wall mount/Installation murale seulementThermal Protection: Inherently protected/
Protection Inherente
Ingress protection: Nema 1, IP

641.472.1747

321

Surface mount LVW shown

Key Attributes:
EcoSlim Edge-Lit LED Technology
Only 1 3/4” / 44.5mm deepHigh efficiency white LEDs
Daylight Quality Light Source
Non-ferrous construction for MRI

Installation:
Easily installed recessed in wallor surface mounted
Rough opening: add 3/8”
to case height and width

The light source for this luminaire is not
replaceable; when the light source reaches its
end of life the whole luminaire shall be replaced.

Sample Configurations:Page 1

Information may be subject to change without notice

2.5.2021

LED Luminous Virtual Window™

Dimensions, Power Consumption Data and Weights:
How to Read the Chart:
The Sky Factory provides four models for each LVW Size:
AC Recessed (LV5-xxxxAR), AC Surface Mount (LV5-xxxxAS), DC Recessed (LV5-xxxxDR), and DC Surface Mount (LV5-xxxxDS).
Case Dimension, Quantity of LEDs, and Weight remain constant for all models in each size.
V AC Input refers to power input to the AC models (LV5-xxxxAR, LV5-xxxxAS), which have internal power supplies.
V DC Input refers to power input to the DC models (LV5-xxxxDR, LV5-xxxxDS) from an externally mounted power supply.
For external power supply specifications, see Electrical section on page 1.

LVW Size
LV5-2240(AR,AS,DR,DS)

LV5-4022(AR,AS,DR,DS)

LV5-3440(AR,AS,DR,DS)

LV5-4034(AR,AS,DR,DS)

LV5-2852(AR,AS,DR,DS)

LV5-5228(AR,AS,DR,DS)

LV5-1864(AR,AS,DR,DS)

LV5-6418(AR,AS,DR,DS)

LV5-3464(AR,AS,DR,DS)

LV5-6434(AR,AS,DR,DS)

LV5-4872(AR,AS,DR,DS)

LV5-7248(AR,AS,DR,DS)

Case Dimension in Inches (Cm)Weight (lbs/kg)

HQty
LEDs

VAC Input(100-277VAC)

V DC Input

W(24VDC)

CaseAlum Trim

Wood Trim

22 (55.9)40 (101.6)

102

0.6A@115V

0.76A

21.4/9.7

4.1/1.9

8.6/3.940 (101.6)

22 (55.9)

102

0.6A@115V

0.76A

21.4/9.7

4.1/1.9

8.6/3.934 (86.8)

40 (101.6)

186

0.6A@115V

1.38A

33.0/15.0

6.3/2.9

13.3/6.0

40 (101.6)

34 (86.8)

186

0.6@A115V

1.38A

33.0/15.0

6.3/2.9

13.3/6.0

28 (71.1)

52 (132.1)

2040.6@A115V

1.52A

35.4/16.1

6.7/3.0

14.0/6.4

52 (132.1)

28 (71.1)

2040.6A@115V

1.52A

35.4/16.1

6.7/3.0

14.0/6.4

18 (46.36)

64 (162.6)

174

0.6A@115V

1.3A

28.0/12.7

5.3/2.4

11.1/5.0

64 (162.6)

18 (46.36)

174

0.6A@115V

1.3A

28.0/12.7

5.3/2.4

11.1/5.0

34 (86.8)

64 (162.6)

258

0.6A@115V

1.92A

52.9/24.0

10.0/4.5

21.0/9.5

64 (162.6)

34 (86.8)

258

0.6A@115V

1.92A52.9/24.0

10.0/4.5

21.0/9.5

48 (121.9)

72 (1828.8)476

1.2/0.5A

3.31A

84.0/38.1

16.2/7.3

34.0/15.4

72 (1828.8)

48 (121.9)476

1.2/0.5A

3.31A

84.0/38.1

16.2/7.3

34.0/15.4

NOTE:
For power consumption of custom sizes, see LVW1 included with the fixture.

641.472.1747

Page 2

Information may be subject to change without notice

2.5.2021