Sky Factorylooser kerning

Sky FactoryTMwww.skyfactory.com•

toll free 1.866.759.3228

Inifinity w/ EcoPlus Installation Instructions(INF-4 Only)
Installation Packet Includes:
Infinity w/ EcoPlus Installation Instructions (INF-4 Only)

EcoPlus LED light box

Luminous SkyTile

One of three Custom EcoPlus Electrical Packets
Custom EcoPlus Electrical Packet (24PS HLG)
Custom EcoPlus Electrical Packet (HLG)

Classic Elevator
15/16” grid

Custom EcoPlus Electrical Packet (Fixture Only)
Luminous SkyTile Installation

Classic perimeter trim

SkyTile Layout
Grid Plan GR1
Grid Plan GR2
Electrical Layout EL1
Electrical Layout EL2
Grid Detail DE2 (INF-4 Only)
Grid Detail DE3-5 (INF-4 Only)

Restraint/sesimic bracing not provided. For recommendations, see Appendix A on page 23.
If any of these documents are missing, please contact Sky Factory for replacements before beginning installation.
Important: All subcontractors involved must have a copy of these specifications. All specifications must be followed in all stagesof on-site manufacture or installation or warranty may be voided. Any deviation in the installation specifications may alter the
final product and could result in a major increase in cost. Please review all documents enclosed before installation.

For technical support at any time during the installation, please call us toll free at 866-759-3228.
We want your installation to go as smoothly as possible. Thank you for choosing Sky Factory.
9/13/2021

Table of Contents
Installation Requirements
Tools and Parts.................................................................. 2-5
Location Requirements...................................................... 6
Suspension Requirements................................................. 7
Electrical Requirements..................................................... 7
SkyCeiling Fixture and Suspension Details........................ 8-9
Fixture and SkyTile Orientation......................................... 10

Installation Instructions

Step 1: Plan for electrical................................................... 11
Step 2: Determine SkyTile orientation............................... 11
Step 3: Transfer grid locations to perimeter trim flange..... 11
Step 4: Bend grid-to-trim clips.......................................... 12
Step 5: Attach suspension brackets to grid mains.............. 12
Step 6: Attach suspension cables to building structure...... 13
Step 7: Hang grid mains.................................................... 13
Step 8: Insert grid-to-trim clips into trim slots.................. 13

Step 9: Install perimeter trim.......................................... 14
Step 10: Install cross-tees that join mains at trim........... 15
Step 11. Level perimeter trim/grid assembly.................. 15
Step 12: Install and wire EcoPlus fixtures........................ 16
Step 13: Install backer rod............................................... 17
Step 14: Wire fixtures to power system anddimmer (where specified).............................. 17
Step 17: Test SkyCeiling electrical.................................... 18
Step 18: Install stabilizers
18(or restraint/seismic bracing where required).... 18
Step 19: Close perimeter trim joints................................ 18
Final Inspection List......................................... 19
Care and Maintenance..................................... 19
Gripple Express No. 2 Installation Guide............ 20
Appendix A: Restraint/Seismic Bracing............. 21

Installation Requirements
Tools and Parts
Tools Provided:3/32” hex wrench
11/32” nut driverTools Needed:
Tools to assemble installation below ceiling
Tools to install suspension system from building structure
1/8” or 9/64” and 11/64” or 3/16” drill bits
Cordless drill/driver and blind rivet tool
Pliers, hammer, screwdrivers, measuring tape, level and other hand tools
Tools for installing electrical and running conduit (where required)

Sky Factory

Page 2

Parts Provided:

NOTE: Quantities vary depending on model
Main Components

Sky Factory EcoPlus fixture
EcoPlus LED light box

Luminous SkyTile

Hanger bracket(x 4-8 depending on fixture)
Classic Elevator

Classic aluminum perimeter trim (8” profile)Standard 15/16” ceiling grid

Sky Factory

Page 3

Parts Provided (cont’d):Perimeter/grid/fixture hardware
Perimeter trim splice plate

Grid-to-trim clip

Backer rod *Corner bracket

2

1

B

B
2

1

2

+
B

UNLESS OTHERWISE SPECIFIED:ADIMENSIONS ARE IN INCHESTOLERANCES:
FRACTIONALANGULAR: MACHBEND
TWO PLACE DECIMAL
THREE PLACE DECIMALAPPLICATIONCHECKEDA

TITLE:B

UNLESS OTHERWISE SPECIFIED:A

ENG APPR.

DIMENSIONS ARE IN INCHESTOLERANCES:
FRACTIONALANGULAR: MACHBEND
TWO PLACE DECIMAL
THREE PLACE DECIMAL

MFG APPR.

COMMENTS:

MATERIAL

USED ON

NEXT ASSY

2

DATE

B

Q.A.

INTERPRET GEOMETRICTOLERANCING PER:PROPRIETARY AND CONFIDENTIAL
THE INFORMATION CONTAINED IN THISDRAWING IS THE SOLE PROPERTY OF<INSERT COMPANY NAME HERE>. ANY
REPRODUCTION IN PART OR AS A WHOLEWITHOUT THE WRITTEN PERMISSION OF<INSERT COMPANY NAME HERE> IS
PROHIBITED.

NAME
DRAWN

1

+

B

SIZE DWG. NO.

DO NOT SCALE DRAWINGSCALE: 2:1 WEIGHT:

INTERPRET GEOMETRICTOLERANCING PER:PROPRIETARY AND CONFIDENTIALREV

RF_RivetCP001116_019
NR
A

FINISHTHE INFORMATION CONTAINED IN THISDRAWING IS THE SOLE PROPERTY OF<INSERT COMPANY NAME HERE>. ANY
REPRODUCTION IN PART OR AS A WHOLEWITHOUT THE WRITTEN PERMISSION OF<INSERT COMPANY NAME HERE> IS
PROHIBITED.

SHEET 1 OF 1

1

MATERIAL

USED ON

NEXT ASSYAPPLICATION

NAME

DATE

UNLESS OTHERWISE SPECIFIED:ADIMENSIONS ARE IN INCHESTOLERANCES:
FRACTIONALANGULAR: MACHBEND
TWO PLACE DECIMAL
THREE PLACE DECIMALTITLE:CHECKED

MFG APPR.
Q.A.
COMMENTS:INTERPRET GEOMETRICTOLERANCING PER:PROPRIETARY AND CONFIDENTIAL
THE INFORMATION CONTAINED IN THISDRAWING IS THE SOLE PROPERTY OF<INSERT COMPANY NAME HERE>. ANY
REPRODUCTION IN PART OR AS A WHOLEWITHOUT THE WRITTEN PERMISSION OF<INSERT COMPANY NAME HERE> IS
PROHIBITED.

MATERIAL

USED ON

NEXT ASSYAPPLICATIONFINISHDO NOT SCALE DRAWING

2

NAME

SIZE DWG. NO.

REV

RF_RivetCP001116_019
NR
A
SCALE: 2:1 WEIGHT:

DO NOT SCALE DRAWINGSHEET 1 OF 1

1

DATE

A

DRAWN
CHECKEDA

DRAWN

ENG APPR.

FINISH

2

TITLE:ENG APPR.
MFG APPR.
Q.A.
COMMENTS:SIZE DWG. NO.

REV

RF_CornerBracket_019
NR
A
SCALE: 1:1 WEIGHT:

SHEET 1 OF 1

* used to center light fixturesin grid pockets

1

Suspension
Suspension bracket

Gripple Express No. 2* **loop type end+* 10’ (3.1m) cable length**Comparable suspension may be used.
See Suspension Requirements, page 7

w/ 8-32 x 5/16” button
head screws and Nylok’s

Electrical
Sky Factory 24PS HLG Power System*

Dimmer switch (optional)*Lutron Diva DVSTV(North America)orJung 240-10(International)*optional MeanWell HLG
or client-provided

Sky Factory

Page 4

Parts Needed:

for AC Source power
Conduit* where required

Electrical wire

1/2” trade size box connector**as per code
In-line switch & wall box (optional)*+*where no dimmer is specified

for DC power
Electrical wire

Conduit* where required

1/2” trade size box connector**as per codefor suspension
Means to attach Gripples to ceiling deck

Flexible cable or chain to stabilize installation in ceiling space*loop end provided*or restraint/seismic bracing where specified
See Step 18
Sky Factory

Page 5

Location Requirements
Infinity w/ EcoPlus SkyCeiling requires selecting a location for the following components:•

SkyCeiling••

Dimmer or in-line power switch

HLG 24PS power system

SkyCeiling••••a minimum of 9’ (2.75m) from floor to bottom of SkyCeiling recommended
a minimum of 6” (15cm) from finished ceiling to top of SkyCeiling recommended
suspension anchor points must meet local and national codes
must be dry and accessible for periodic cleaning

Junction Box

Source AC

Dimmer24PS HLG
Power System

Power system

Dimmer••wall box not provided•

Lutron Diva dimmer shown•must be dry, dust-free andaccessible for periodic cleaning
SkyFactory 24PS HLG shown

Sky Factory

Page 6

Suspension Requirements
Fixture Suspension
Suspension system (provided) which receives Gripple Express #2 (provided) anchored to building structure:
See drawings GR1 and GR2 and cross sections DE2 and DE3-5 included.
Suspension anchor points not provided and must meet local and national codes
Alternate means to hang suspension system from building structure anchor points, if used, must meet local and national codes.
SkyCeiling must be installed level
Assembling SkyCeiling in position recommended. Assembling smaller SkyCeilings on floor and mechanically lifting into position
is an option; however, caution must be taken. Infinity perimeter is a trim system and cannot be excessively torqued.

Most building codes require non-structural building components to be restrained. Sky Factory also recommends restraint
in accordance with local building code requirements. Please consult with the building code professional having jurisdiction
over the project to determine appropriate restraint requirements for this instllation. Restraints are not included in this kit.

SkyCeiling Dimensions and Weights
INF-4
8” (20.3cm) deep
4’ 3 1/8 (129.9cm) outside diameter
51 lbs (23.2kg); 13lbs (5.9kg) per suspension point

Electrical Requirements
At 24V DC:
INF-4 @ 3.4A, 80.5W
See one of three electrical packets:
Custom EcoPlus Electrical Packet (24PS HLG),
Custom EcoPlus Electrical Instructions (HLG), or
Custom EcoPlus Electrical Instructions (Fixture Only)
Electrical work must be performed by a qualified electrician who is familiar with DC lighting systems
and must conform to all local and national codes.
Sky Factory

Page 7

SkyCeiling Suspension and Fixture Details
IMPORTANT: Assembling SkyCeiling in position is highly recommended. Perimeter is a trim system only.
Assembled SkyCeiling cannot be excessively torqued.
NOTE: Gripple suspension cables removed for clarity
1. Mains suspend from building structure with suspension brackets
2. Trim attaches to ends of mains with grid-to-trim clips
3. Trim is joined with splice plates
4. Cross tees attach to mains with corner brackets

2

3
1

4

See GR2
for Point 2 & 4 details
7. EcoPlus fixtures insert in grid pockets
8. Fixtures are wired together
9. Backer rod (as needed) centers fixtures in grid pockets

7
8
B2

B2

B2

B2

B2

9

NOTE: Gripple suspension cables removed for clarity
Sky Factory

Page 8

EcoPlus components:

Hanger brackets hold fixture together
and provide suspension where required.
NOTE: See page 8 for assembly details.

EcoPlus Back Panel
LED Bar
EcoPlus Frame
Hanger Bracket
SkyTileElevator
Ceiling Grid

Inside face of Elevators should ideally sit:•

1/32 inch (.79mm) back of leading edge of grid and•1/32 inch (.79mm) to 1/16 inch (1.59mm) backof leading edge of curved perimeter angle.

Sky Factory

Page 9Fixture and SkyTile Orientation
Fixtures MUST be installed so SkyTiles fit SkyTile Layout.
See SkyTile Installation Instructions and SkyTile Layout included.
To facilitate correct SkyTile placement, fixtures are labeled on top of backpan and on SkyTile:

In all installations with more than one fixture,
an elevator with logo is provided.
Fixture with elevator is installed in location
noted on SkyTile Layout.

All fixtures
are location specificand are labeled accordingly.
Refer to Grid Plan GR1 and/or SkyTile Layout for
proper locations and orientations.

Important:
Quick release labels are for installation
purposes only.
They orient the location and directionof each tile in the SkyCeiling.
Labels MUST be removed
once the SkyCeiling is fully installed
and checked for proper orientation.

Sky Factory

Page 10

Installation Instructions
Step 1: Plan for electrical•

See Location Requirements on page 6 and Custom EcoPluS Electrical Packet provided

Step 2: Determine SkyTile orientation•

See page 10•

IMPORTANT: Be sure to orient the fixtures following the SkyTile Layout sheet. If the SkyTiles are improperly oriented,
the fixture or fixtures will have to be removed from the SkyCeiling so the SkyTile can be properly oriented.

Step 3: Transfer grid locations to perimeter trim flange

A2

A1

NOTE: Curve of trim section may not be even and follow template; if not, gently bend to conform to curve on template.
This will expedite grid and fixture installation in Steps 9-13.

Lay each trim section onto
corresponding plot
and transfer grid location marks
to inside of flange.

Sky Factory

Label each section accordingly
for future reference

Page 11

Step 4: Bend grid-to-trim clips
Clip inserts in lower trim slot
and goes shoulder up.
NOTE:
Leg will distort less
if clip is removed
and grabbed at basewith needle noseshoulder up

Insert at angle and twist clockwise to lock.

Protruding leg is bent to appropriate angle
to receive grid web

Step 5: Attach suspension brackets to grid mains
See Bracket and Suspension Detail GR2 for bracket locations
and hardware details

secure with 8-32 x 5/16” button headscrews and Nyloks provided
mount brackets and insert screws
on side of grid
toward center of SkyCeiling
NOTE: This will allow EcoPlus fixtures
to insert more smoothly

Sky Factory

Page 12

Step 6: Attach suspension cables to building structure*
See:•

Bracket and Suspension Detail GR2 for SkyCeiling suspension points•

Suspension Requirements on page 7 for SkyCeiling weights•

Gripple Express No. 2 installation sheet on page 20.

•

Alternate means to hang suspension system, if used, must meet local
and national codes.

Step 7: Hang grid mains
See Bracket and Suspension Layout GR2 for suspension points andGripple Express No. 2 installation sheet on page 20.
Alternate means to hang suspension system, if used, must meet local andnational codes.

Step 8: Insert bent grid-to-trim clips into perimeter trim slots
For insertion and bending details, see Step 4

Sky Factory

Page 13

Step 9: Install perimeter trim
Attach trim to cut grid ends following GR1 and GR2.

IMPORTANT: Cut grid length varies 1/16 - 1/8”
Determine grid opening on GR1 before securing clip!

NOTE:
See GR2 detailfor which side of gridto attach clip

Bottom of grid bulb rides
against top of clip.

Attach grid to clip
with two 1/8” steel pop rivets provided.
Rivet location is criticalfor corner brackets.
See Step 10

Grid flange sitson bottom lip of trim

Connect trim sections with splice plates
in both top and bottom slots.

Stagger plates to either side of joint
DO NOT OVERTIGHTEN SCREWS.
Excessive torque will result in deformationof trim on finished surface.
Hex wrench provided in installation kit

Sky Factory

Page 14

Step 10: Install cross tees that join mains at perimeter trim
See also GR1 and GR2.

cross-tee

main

cor
n

er

36”
centerof grid
tocenterof grid

bra

cke

t (x

4)

Rivets in grid-to-trim clip fall in oval hole

main

Rivet corner bracket to main using
noted holes to avoid clip

Where necessary, rivet corner bracket
to tee using back two holes
to avoid large dia. hole in end of tee

Step 11: Level perimeter trim/grid assembly
Level the trim/grid assembly before installing the EcoPlus fixtures. Access to the assembly is easier, andadjustments, if needed, are more accessible.

Sky Factory

Page 15

Step 12: Install and wire EcoPlus fixtures
Insert EcoPlus fixtures into appropriate grid pockets and wire fixtures together
See GR1 and Fixture and SkyTile Orientation on page 10 for fixture layout and orientation
See Custom EcoPlus Electrical Packet for electrical instructions
IMPORTANT:•

Fixture in the center of the installation may need to be wired before perimeter fixtures are installed•

Do not install box connectors on side of junction box next to side of light fixture.
It will make some fixtures difficult to install, wire, and if necessary, remove

Mains/suspension
1. Install center fixture firstaa. insert side next to suspension bracket first, thenb. drop opposing side in

2

b
a

b

Fixture may need to be wedged past suspension hardware
2. Install perimeter fixtures next
a. insert corner of curved side first, thenb. drop opposing side in
Fixture may need to be wedged past suspension hardware

2

1

a

a

b
b

Sky Factory

2

b

2

a

Page 16

Step 13: Install backer rod
Backer rod installs between perimeter Elevators and trim. It centers fixture in grid opening
and prevents light leaks. See DE2.

B2

B2

B2

B2

B2

One end of backer rod is pushed down
between Elevator and trim
leaving other end available at top
so it can be easily removed

Inside face of Elevators should ideally sit:•

1/32 inch (.79mm) back of leading edge of grid and•1/32 inch (.79mm) to 1/16 inch (1.59mm) backof leading edge of curved perimeter angle.

Step 14: Wire fixtures to power system and dimmer (where specified)
See Custom EcoPlus Electrical Packet provided
IMPORTANT: Fixtures in the center of the structure may need to be wired before perimeter fixtures are installed
Install all electrical in accordance with local and national codes.

Sky Factory

Page 17

Step 15: Test SkyCeiling electricalPower up SkyCeiling and make sure all fixtures are on and SkyCeiling is evenly lit. If dimmer is included,
make sure ceiling dims evenly.

Step 16: Install stabilizers (or restraint/seismic bracing where required)
Skip this step and go to Appendix A if restraint/seismic bracing is specified
Run fine gauge flexible wire (or comparable) from end of main diagonally up to building structure
to reduce sway of SkyCeiling.

Step 17: Close perimeter trim joints
Trim joints may begin to separate from the installation process. Pull joints back together

Sky Factory

Page 18

Final Inspection List
Are all the fixtures seated down against the grid flange?
•  If fixtures are not seated down against the flange, light leaks could result.
In grid ceiling applications, do all the fixtures sit evenly in the grid?
•  If not, Elevator alignment may need adjusting.
•  If grid is not installed square, fixtures may sit unevenly in the opening. If so, adjust grid so it is square.
Do all the fixtures sit evenly next to one another?
•  If not, Elevator height or side to side position may need to be adjusted.
Is the image evenly lit?
•  If there are shadows, dark spots, or bright lines on the image, clear off the back of the SkyTile.
•  If one or more SkyTiles are dark, one or more fixtures are not working. Re-check wiring.
Does the SkyCeiling image match the SkyTile Layout image?
•  Make sure the tiles are in the correct position and orientation. If the SkyTile Layout has a head location,
make sure the SkyCeiling is properly oriented in the room. If not, they should be reinstalled.
Have the arrow-labels been removed once the image has been verified? If not, remove them now.
•  Quick release labels MUST be removed once the SkyTiles are fully installed and checked
for proper orientation.

Care and Maintenance•

Avoid scratching SkyTiles and Elevators when cleaning.

•

Once installed, SkyTiles and Elevators can be cleaned in place.

•Use mild soap and water solution, and a soft, non-abrasive cloth.

•

DO NOT wet edges of SkyTiles. Water may cause image film to de-laminate.

Sky Factory

Page 19

Gripple Express No.2
A push-button Gripple fastener solution for quick and easy suspension and height adjustmentof light fixtures, signage, HVAC, mechanical, and electrical services, without the need for arelease key.
ADVANTAGES• Up to 6 times faster to install than traditional methods• Keyless - no tool required for adjustment• Ergonomic buttons allow rapid adjustment• Discreet and aesthetic design• Load rated at 100 lbs with a 5:1 safety factor• Supplied as a ready-to-use kit

INSTALLATIONRELEASE2

PRODUCT DIMENSIONS

1

END FIXING

L

D

W

Cable Diameter

L (in)⁄64”

1 1⁄8”

5* This product is silicone freeW (in)⁄8”

7

D (in)⁄16”

7

Each ready-to-use kit comes with an end fixing ofyour choice. Standard hanger lengths are available
in 5ft to 30ft lengths; other lengths available
upon request.
For further detailed information on any of our end
fixings, please visit our website or contact us using
the information below.

Gripple Inc | 1611 Emily Lane | Aurora, IL 60502 | USA
Tel +1 866 474 7753 Fax +1 800 654 0689 email usinfo@gripple.com
PI-47-USAwww.gripple.com

Sky Factory

Page 20

Appendix A: Restraint/Seismic Bracing
Most building codes require non-structural building components to be restrained. Sky Factory also recommends
restraint in accordance with local building code requirements. Please consult with the building code professional
having jurisdiction over the project to determine appropriate restraint requirements for this instllation. Restraints
are not included in this kit.

Restraint for Infinity installations where anticipated seismic activity will be light (IBC seismic design categories A & B)
can be accomplished by installing a pair of crossed cables 2’ in from each edge of the assembly. These cables should
attach to the support beam and be sloped no more than 450 from horizontal.
In areas where anticipated seismic activity will be moderate to severe, the crossed cables should be replaced with abracing system more appropriate for the forces that will be encountered.
Testing conducted at the Structural Engineering Earthquake Simulation Laboratory, located at the State Universityof New York - Buffalo campus, produced satisfactory results with rigid bracing fabricated from 1/2” EMT conduit.
The tested bracing system consisted of a vertical member extending from the support beam to the structure above
near each corner of the cloud. These members were positioned at the main beam/support assembly. Two additional members were fastened to the bottom of the vertical and extended to the structure at an angle not exceeding
450 from horizontal. These members were parallel to the sides of the cloud.
Restraint/bracing systems should be approved by the project design team and reviewed with local building
department.

Sky Factory

Page 21