Profile® III Filters
Data Sheet MEPRO3ENdApplications
CMP slurry, Inkjet inks, DI water

Description
Profile III filters are all polypropylene innovative depth filters.
The fibers in Profile III filters may be considered continuous.
No binder resin is used – the fibers are “bonded” by intertwining
during the manufacturing process. As a result, Profile III filtersshow no media migration. Profile III filters can be expected toyield longer service life and lower your total filtration costs.

Revolutionary Cartridge Construction
Longer service life is maintained by its continuously gradedpore structure for built in prefiltration, In addition, because ofProfile III's unique larger core and innovative fiber structure,
Profile III's initial pressure drop is up to 50% (0.3 μm) and 30%(1.0 μm ) lower than Profile II's pressure drop with no reductionin efficiency, for equivalent grades.

MCY type

Specifications
Materials of Construction
Components

Materials

Filter Medium

Polypropylene

Core

Polypropylene

Endcaps and Cage (MCY, AB type)

Polypropylene

Gasket (MCY type)

EPDM (Consult factory for other materials)

O-ring (AB type)(Size : Code 25)(Size : Code 7)

EPDM (Consult factory for other materials)
222 double O-ring flat end
226 double O-ring bomb fin

Removal Rating

0.3 μm, 1.0 μm

Maximum Temperature182 ºC / 180 ºF

Maximum Differential Pressure

0.4 1 MPa / 60 psid @ 30 ºC / 86 ˚F
0.34 MPa / 50 psid @ 50 ºC / 122 ˚F
0.2 1 MPa / 30 psid @ 70 ºC / 158 ˚F
0.1 0 MPa / 1 5 psid @ 82 ºC / 180 ˚F

1 Consult your local Pall representative on the condition at high temperature over 49 ºCAB typeTypical Flow Characteristics - 1cP fluid, 20 ºC5014045100

Clean pressure drop (kPa)

Clean pressure drop (kPa)120
Profile II 0.3 μm

806040

Profile III 0.3 μm

20002468101240

Profile II 1.0 μm

353025

Profile III 1.0 μm

20151050024681012

Flow rate (L/min)

Flow rate (L /min)

Part Numbers / Ordering Information2
MCY type : MCY 100 1 W 2 J254
AB type: AB 1 W 2 25J

AB type: AB 1 W 2 7J

Table 1Code

Cartridge Nominal Length

Cartridge Nominal Diameter

1254 mm / 10 inch

70 mm / 2.75 inch

2508 mm / 20 inch

70 mm / 2.75 inch

3762 mm / 30 inch (AB type only)

70 mm / 2.75 inch

Table 2CodeRemoval Ratings010

1 .0 μm003

0.3 μm2 For 4” Code 25 and 1” Test Filters, please contact your local Pall representative for price and availability.

Visit us on the Web at www.pall.com/microelectronics
Contact us at www.pall.com/contact
Microelectronics
25 Harbor Park Drive
Port Washington, NY 11050+1 516 484 3600 telephone+1 800 360 7255 toll free USNihon Pall Ltd.
6-5-1, Nishishinjuku,Shinjuku-ku
Tokyo 163-1325 Japan+81 3 6901 5700 telephone+81 3 5322 2109 fax

Pall Corporation has offices and plants throughout the world. To locate the Pall officeor distributor nearest you, visit www.pall.com/contact.
The information provided in this literature was reviewed for accuracy at the time ofpublication. Product data may be subject to change without notice. For current information consult your local Pall distributor or contact Pall directly.
IF APPLICABLE Please contact Pall Corporation to verify that the product conforms toyour national legislation and/or regional regulatory requirements for water and foodcontact use.

© Copyright 2022, Pall Corporation. Pall,, and Profile are trademarks of PallCorporation. ® Indicates a trademark registered in the USA.

MEPRO3ENd

October 2022