EXPLOSION PROOF LED CEILING LIGHT■ Half of the consumption electricity compare with the ceiling light ■ There is seldom loss of the power supply ata high power factor ■ Longer life 40,000h ■ There are few ultraviolet rays and fever and is strong in lowtemperature ■ AC100-240V +-10% wide range power supply adoption ■ It conform to EN55015/EN61547 As
noise measures ■ Certiﬁcate：11ATEX0051X/01 EExdIIC-T6 Zone1＋Zone2,NK ■ Protection level：IP67■ Ambient temperature：-20℃〜+55℃ ■ Cable entry：2×3/4 NPT (2×M20 We can produce it)■ Material:Body Corrosion resistance aluminum, glove Impack resistant／【We can also produce glass type】■ Terminal board : PLUG-IN terminal until 10mm³. L,N,P,E. Loop connection is possible.

TYPE: XFR120-21060 fluorescent lamp 20W×1 light equivalency／
XFF220-21060 fluorescent lamp 20W×2 light equivalency
Model

XFR120-21060

XFF220-21060

Range of input voltage

AC100-240V ±10%
1φ 50/60Hz

AC100-240V ±10%
1φ 50/60Hz

Input current

11W

19/18.5W

Power factor

0.96(100V)/0.93(220V)

0.99(100V)/0.92(220V)

Luminous flux

900 lm900 lm×2

XFR120-21060

XFR220-21060

TYPE: XFR140-21060 fluorescent lamp ４0W×1 light equivalency／
XFF240-21060 fluorescent lamp 40W×2 light equivalency
Model

XFR140-21060

XFF240-21060

Range of input voltage

AC100-240V ±10%
1φ 50/60Hz

AC100-240V ±10%
1φ 50/60Hz

Input current

20.5/20W

38/37W

Power factor

0.99(100V)/0.93(220V)

0.99(100V)/0.92(220V)

Luminous flux

1800 lm

1800 lm×2

XFR140-21060

XFR240-21060

14

LED HAND LAMP AND LED DOWN LIGHT
TYPE : LHG-A11-D／A12-D／LHG-D10■ The brightness that is near to a 100W incandescent electric lamp work light.
■ 10-13W a little as for the consumption electricity. About 1/10 of the incandescence work light■ Longer life 40,000h ■ The glove has taking a polycarbonate that is good impact resistance and weather resistance.
■ An appliance does not become hot even if an appliance turns on for a long time
■ Prepare two types of AC100V and AC200V■ The DC type supports the wide input voltage range ■ It conform to EN55015/EN61547 As noise measures■ AC types are with dimming function (Dimmer not included)
Model

LHG-D10

LHG-A11-D

LHG-A12-D

Range of input voltage

DC24V (DC20-32V)

AC100 (AC100-120V±10％)AC220V (AC200-240V±10％)

Input current

Approx.0.42A

Approx.0.1A

Approx.0.06A

Power consumption

10W

Max.13W

Max.12W

Power factor

─0.9

0.9

Color temperature

5000K

5000K

5000K

Luminous flux

950lm

930lm

900lm

WeightApprox.0.8kg

0.8kg

0.8kg

Color

7.5BG7/2

LED DOWN LIGHT

TYPE: LDW-150Series■ Low power consumption ■ Longer life 40,000h■ We have the single color type that is with dimmer switch and no switch■ We have a product in conformity to an AC type and DC type
■ We have a full color type(red,white) and a reshuﬄing type
■ It conform to EN55015/EN61547 As noise measuresionensdimcutle
PanModelcolor temperature Dimmer function color temperature

Input current

Luminous flux Luminous flux

WeighExternal power
supply presenceon

LDW-150MA1-A×○

LDW-150MA2-A

3000K

AC100-120V ± 10％

Max.13W

750 lm0.56×○3000K

AC200-240V ± 10%

Max.13W

750 lm0.56onLDW-150MD×○DC20-32V

Max.11W

585 lm0.58offLDW-150MNA

3000K××

3000K

AC100-240V ± 10%

Max.12W

585 lm0.56

on

LDW-150MND××DC20-32V

Max.10W

585 lm0.58

off

LDW-150MA1AM

3000K

○○―――

AC100V-110V ± 10%

Max.13W

130 lm0.56on■ Single color power supply mass

0.15kg■ Weight for power unit withEXPLOSION PROOF LED CEILING LIGHT■ Explosion proof grade : EExd ⅡC T6/4/3 ZONE 1 + ZONE 2■ Certiﬁcate No.: INERIS 15ATEX0006X , IECEx INE 15.0008X■ Ambient temperature : -20℃〜40℃■ Protection degree : IP66
■ Material : corrosion proof aluminum alloy ( Guard : SUS)
■ Color : 7.5BG7/2■ Cable gland : 4 x NPT3/4■ Input voltage : 100V〜240V■ RATING : Max. 11W

160.32kg

The dimmer switch as option

Model : LF1-01

Fitting hole