Sensepoint

The Sensepoint range of flammable,
toxic and Oxygen gas detectors offers
users a cost-effective solution to theirgas monitoring needs

Sensepoint

One-Stop Shop• 	Flammable, toxic and Oxygenversions available• Suitable for indoor or outdoor use• IP65 as standard

Proven Sensor Technology••••

SurecellTM electrochemical sensors
Poison resistant catalytic bead
Fast and reliable
Typical 2 to 5 years operational life

ATEX Certified• 	Complies with the latest Europeanstandards• Hazardous area and performanceapprovals• Can be used for uncertified applications

Easy to Use•••

Factory set operation
Simple sensor replacement
Minimal training required

Friendly Installation• Universal junction box• One box, three entries• Metric and NPT compatibility• 	Includes earth continuity platefor enhanced protection against RFI

Range of Accessories•••

Weather Housing (IP66)
Flow adaptor
Collecting cone

The Sensepoint range of flammable, toxic
and Oxygen gas detectors offers users acost-effective solution to their gas monitoringneeds, in or out of doors and even in
potentially explosive atmospheres. Suppliedwith a pre-wired junction box, this detector
can be installed using conduit or armoured
cable and glands depending on the specificneeds of the application.
Sensepoint flammable and toxic gas detectors
are designed for use in potentially explosive
atmospheres, and allow for easy access toterminals via the hinged lid of the junction box.
Installation should follow national guidelines using
suitably approved armoured cable and glands
or conduit.
Supplied with an earth continuity plate for increased
resistance to the effects of RFI, the junction box
offers the installer a choice of ½”, ¾” and M20
connection via conduit or armoured cable and Ex ecertified cable glands. Terminals are suitable for use
with screened 0.5mm2 (20AWG) to 2.5mm2(14AWG) cross sectional area cable, as needed toensure minimum operating voltage at the detector,
depending upon installed cable length.
Sensepoint flammable, toxic and Oxygen gas
detectors are designed for direct connection
with the Honeywell Analytics’ range ofTouchpoint controllers.
Contact Honeywell Analytics for details.

Installation Details

Dimensions

156.0mm (6.1")
102.0mm (4.0")¾”NPTCable entry

Detector
certification
information

The junction box is suitable for mounting
onto any suitable flat surface able tosupport the weight of the unit such thatwhen installed, the sensor is in a downward
position. For ceiling mounting an optional
bracket is available to allow for this.

M20
cable entry

102mm (4.0")

Mounting
lug x 2(R3.5mm)

76.5mm (3.0")34.0mm (1.3")

½”NPT
cable
entry

202.0mm (8.0")

Sensepoint flammable and toxic gas
detectors offer multiple cable entry sizes
as standard and allow for quick and easy
installation via the hinged lid of the junction
box.

75.0mm (3.0")

Enclosure
Detectorgas type

Cable can be entered into the junction boxes
via a gland or conduit through one or morepositions in the top or sides of the unit.

Sensorcertification
information

SensorPlastic retainer(with externalhydrophobic barrier)ø 60.0mm (2.4")

Flammable version

Toxic and Oxygen version

Terminal arrangement

Terminal arrangement

Screen(braided wire)

Sensitive
element(brown)

Earthterminal
Nonsensitiveelement(blue)

Center tap(white)+ Supply (red)Electrical connections

Signal (blue)

Electrical connections
Detector

Controller+VE

11Detector

Controller+VE+VE

112233+VE

ActiveSignal2233Signal

SignalNon-active-VE

3 wire mV bridge circuit-VE

RL100ohm-VE

2 wire 4-20mA (sink)

SignalTechnical Summary

General specification
Use

Cost-effective, fixed point gas detector for the protection of personnel and plant from flammable, toxic and Oxygen gas hazards

Detectable gases
Gas 		

Measuring range 			Ident Name

1#MinMaxF		Flammable

0-100% LEL			

-40°C / -40°F

50°C / 122°F

O		Oxygen

0-25% VOL			-15°C / 5°F

40°C / 104°F

2

Operating temperature*

3

C		Carbon Monoxide0-200ppm

0-500ppm		

-20°C / -4°F

50°C / 122°F

H		

Hydrogen Sulphide +0-50ppm

0-20ppm-25°C / -13°F

50°C / 122°F

G		

Hydrogen0-1000ppm			

-5°C / 23°F

40°C / 104°F

L		

Chlorine

0-5ppm0-15ppm		

-20°C / -4°F

50°C / 122°FS		

Sulphur Dioxide

0-15ppm

0-50ppm		

-15°C / 5°F

40°C / 104°F

N		

Nitrogen Dioxide

0-10ppm			

-15°C / 5°F

40°C / 104°F

A		Ammonia

0-50ppm-20°C / -4°F

40oC / 104°F+ SureCell

TM+Sensing Technology

0-100ppm

0-1000ppm		

Standard range			#*Check certified temperature

Construction
Electrical

Flammable (0-100%LEL)
3 wire mV bridge
2.9-3.5V, 0.7W
200mA constant current

Toxic & Oxygen2 wire loop powered 4-20mA(plus screen)
16-30Vdc, O.9W

Junction Box
Earth continuity plate
BK4 terminal block (4 way)
4 x 0.5mm2 (20AWG) to 2.5mm2 (14AWG)
1 x M20, 1 x ¾” NPT, 1 x ½” NPTMaterial

Polyphenylene Sulphide (PPS)Polyphenylene Sulphide (PPS)Fire retardant GFPWeight

190g

185g (205g Oxygen)

600g

Certification

II 2GD
Ex d IIC T6 Gb
Ex tb IIIC A21 Db IP67 T85ºC(Tamb -40ºC to +55ºC) or T100ºC(Tamb -40ºC to +70ºC) or T135ºC(Tamb -40ºC to +80ºC)
Baseefa08ATEX0265X
IECEx BAS08.0068X

II 2 GD Ex d ia IIC T4 Gb Tamb -40ºC
to +65ºC
Ex tb IIIC A21 IP67 T135ºC Db
Baseefa08ATEX0263X
IECEx BAS08.0070X

II 2GD
Ex e IIC T6 Gb Tamb -40ºC to +50ºC
Ex t IIIC T85ºC Db IP66
Sira 06ATEX3185

Applicable standards

This product complies with the relevant CE standards including:
EMC to EN50270, Flammable to EN60079-29-1, Toxic to EN445544 (H2S only)

EnvironmentalIP rating

IP65 standard, IP66 with weather protection in accordance with EN60529:1992

Operating temperature

Dependent upon gas type and certification

Operating humidity range

Continuous: 20-90% RH (non condensing), Intermittent: 10-99% RH (non condensing)Operating pressure

90-110kPa

Storage conditions

Instrument -40°C to +50°C (-40°F to +122°F)*Oxygen detection products must only be used to detect Oxygen depletion in airOrdering Information

Ordering Information

e.g. SPSTAX H 1 = SPSTXXH1GAS TYPERANGEF Flammable
O Oxygen
C Carbon Monoxide
H Hydrogen Sulphide
G Hydrogen
L Chlorine
S Sulphur Dioxide
N Nitrogen Dioxide

123}

Refer toDetectable Gases
Table Above

Standard Supply	Each detector is supplied complete with junction box, multiple cable entries, earth continuity plate,hinged lid and instruction leaflet, all sealed in a plastic bag inside a shipping carton
Shipping Details

Shipping carton dimensions: 160mm (6.3”) (L) x 215mm (8.5”) (W) x 80mm (3.1”) (D)Approximate weight: 800g

Optional Accessories

02000-A-1645

Calibration gas flow housing (for flammable & toxic)

00780-A-0160

Right angle mounting bracket for ceiling mounting

02000-A-1640		

Weather Housing for use with flammable detector
including remote gassing nozzle

02000-A-1635		

Weather Housing for use with toxic/Oxygen detector
including remote gassing nozzle

02000-A-1642
Calibration Equipment

Contact Honeywell Analytics Representative

Collecting cone for use with flammable detector

Our Product Range

Fixed Gas Monitoring

Portable Gas Monitoring

Honeywell Analytics offers a wide rangeof fixed gas detection solutions for adiverse array of industries and applications
Find
out more
including:Commercial properties, industrial
www.honeywellanalytics.com
applications, semiconductor manufacturers,energy plants and petrochemical sites.
Contact Honeywell Analytics:» Detection of flammable, Oxygen and toxic
gases (including exotics)
Europe, Middle East, Africa, India»
Innovative use of four core sensing
Life Safety Distribution AG
technologies – paper tape,
Weiherallee 11a
electrochemical cell, catalytic bead
CH-8610and Usterinfrared
Switzerland»
Capability to detect down to Parts Per
Tel: +41 (0)44 943 4300
Billion (ppb) or Percent by Volume (%v/v)
Fax: +41 (0)44 943 4398
»Cost effective regulatory complianceIndia Tel: +91 124 4752700
solutionsgasdetection@honeywell.com

When it comes to personal protection fromgas hazards, Honeywell Analytics has a wide
range of reliable solutions ideally suited foruse in confined or enclosed spaces.
These include:

At Honeywell Analytics, we believe in thevalue of great service and customer care.
Our key commitment is providing complete
Findmoreandouttotalcustomer satisfaction. Here are justa few of the services we can offer:www.honeywellanalytics.com» Detection of flammable, Oxygen and» FullHoneywelltechnical support
ContactAnalytics:» Expert team on hand to answer
questions
queries
Europe,Middleand
East,
Africa, India» out
Multi-gas
Find
more transportable monitors – usedfor temporary protection of area
www.honeywellanalytics.com
during site construction andmaintenance activities
Contact Honeywell Analytics:

Americas
Honeywell Analytics Inc.
405 Barclay Blvd.
Lincolnshire, IL 60069
USAFind+1out
more
Tel:
847955 8200
Tollfree: +1 800 538 0363
www.honeywellanalytics.com
Fax: +1 847 955 8210
detectgas@honeywell.com
Contact Honeywell Analytics:

Europe, Middle East, Africa, India
Life Safety Distribution AG
Weiherallee 11aCH-8610 Uster
Switzerland
Tel: +41 (0)44 943 4300
Fax: +41 (0)44 943 4398
India Tel: +91 124 4752700
gasdetection@honeywell.com

Americas
Honeywell Analytics Inc.
405 Barclay Blvd.
Lincolnshire, IL 60069
USATel: +1 847 955 8200
Toll free: +1 800 538 0363
Fax: +1 847 955 8210
detectgas@honeywell.com

Asia
Pacific
Europe,Middle East, Africa, India
Honeywell
Asia
Life Safety Analytics
Distribution
AGPacific#508,
Kolon11a
Science Valley (I)Weiherallee
187-10Guro-Dong,
Guro-GuCH-8610UsterSeoul,152-050
Switzerland
Korea
Tel: +41 (0)44 943 4300
Tel:6909
Fax:+82+41(0)2(0)449430300
4398
Fax:0329
India+82
Tel: (0)2+912025
124 4752700
analytics.ap@honeywell.com
gasdetection@honeywell.com

Americas
Honeywell Analytics Inc.
405 Barclay Blvd.
Lincolnshire, IL 60069
USA
Tel: +1 847 955 8200
Toll free: +1 800 538 0363
Fax: +1 847 955 8210
detectgas@honeywell.com

Asia Pacific
Honeywell Analytics Asia Pacific#508, Kolon Science Valley (I)187-10 Guro-Dong, Guro-Gu
Seoul, 152-050
Korea
Tel: +82 (0)2 6909 0300
Fax: +82 (0)2 2025 0329
analytics.ap@honeywell.com» Single gas personal monitors – worn by
the individual» Multi-gas portable gas monitors – usedfor confined space entry and regulatorycomplianceTechnicalAmericas Services
EMEAI:
HAexpert@honeywell.com
HoneywellAnalytics Inc.
US:
ha.us.service@honeywell.com
405 Barclay
Blvd.
AP:
ha.ap.service@honeywell.com
Lincolnshire,IL 60069Asia Pacific
Honeywell Analytics Asia Pacific#508, Kolon Science Valley (I)187-10 Guro-Dong, Guro-Gu
Seoul, 152-050
USA
www.honeywell.com
Korea
Tel: +1 847 955 8200
Tel: +82 (0)2 6909 0300
Toll free: +1 800 538 0363
Fax: +82 (0)2 2025 0329
Fax: Note:+1 847 955 8210
PleaseWhile every effort has been made to ensure accuracy in this publication, no responsibility
can be accepted for errors or omissions.
analytics.ap@honeywell.com
detectgas@honeywell.com
Data may change, as well as legislation, and you are strongly advised to obtain copies of the most recently issued regulations,standards, and guidelines. This publication is not intended to form the basis of a contract.

Asia Pacific

H_Sensepoint_DS0326_V6_EMEAI
Honeywell Analytics Asia Pacific01/12©
2012 Honeywell
Analytics Valley (I)#508,
Kolon Science

187-10 Guro-Dong, Guro-Gu
Seoul, 152-050
Korea

Technical Services
EMEAI: HAexpert@honeywell.com
US:
ha.us.service@honeywell.com
AP:
ha.ap.service@honeywell.com
www.honeywell.com

Fully Distribution
equipped workshops
to ensureLife» SafetyAGquick 11aturnaround on repairsWeiherallee» Comprehensive
service engineer network
CH-8610
Uster
Switzerland» Training on product use and maintenanceTel:(0)44calibration
943 4300service» +41Mobile
Fax: +41 (0)44 943 4398
» Customised programmes ofIndia Tel:
+91 124 4752700 maintenancepreventative/corrective
gasdetection@honeywell.com» Extended warranties on productsTechnical Services
EMEAI: HAexpert@honeywell.com
US:
ha.us.service@honeywell.com
AP:
ha.ap.service@honeywell.com
www.honeywell.com

10720

toxic gases

Technical Services