Gas Detection

Sensepoint XRL
Fixed Gas Detector
Sensepoint XRL is a fixed point gas leak detector that is designed tomeet the needs of industrial applications. With over 50 years experiencein gas leak detection, Honeywell offers a flexible range of highly-reliable
sensing devices to meet those needs.
• Quick installation• Rapid configuration• Simple to operate• Straightforward to maintain
Honeywell innovation enables customers to pair the gas detector with
their mobile phone, and then use an app to perform many tasks related
to installation, commissioning and maintenance.

Visual Integration

Flexible Output Options
Sensepoint XRL is available with either mA loop analog output
or Modbus RTU. The result is a flexible solution that can easily beincorporated into legacy systems as well as new installations.

Easy Control and Maintenance
Sensepoint XRL's smartphone interface makes for much faster
calibration, configuration and bump tests. Inspecting the status andsettings of individual Sensepoint XRL detectors is simple. Use themobile app to:• Read gas concentrations in real-time• Reconfigure settings• Check unit histories

Automated Reporting
Increase the efficiency of your operations and reduce administration
time. The app and Sensepoint XRL provides easy access to diagnostic
information and generates calibration reports at the touch of a screen.

Compatible System Controller
Touchpoint Plus is the perfect complement to Sensepoint XRL, providing
an intuitive, easy to operate gas detection solution to meet the needs ofyour business.

Clean aesthetics and a choice of colors meanthat the detector appearance can be selected
to compare or contrast with the environment inwhich it is being used.

Typical Applications• Manufacturing facilities and factories• Water treatment plants• Battery charging facilities• Vehicle test facilities• Petrochemical plants• Fuelling depots

Accessories• Calibration cap• Collecting cone
• Pole Mount Bracket Kit• Duct Mount Kit• Weather Protection• Flow Housing

F E AT U R E S & B E N E F I T S• Choose from a
range of mA orModbus output
versions for flexible
system design tomeet thecustomers
requirements.

• Selectable sourceor sink current foranalog output
enables one
detector to besuitable for bothsystemconfigurations.

• The ingress
protection of NEMA
4X/IP66 allows
units to be installedin outdoor
environemtns.
• Simplified
maintenance withfamiliar
smartphone
technology saves
money and time.

• Multi-color visualindicator to show
status makes it
easier to  know thedetector status
immediately andidentify detectorsthat require
attention or arewarning of danger.

• Manage thedetector without
making a physicalconnection.
Remove the needfor physical accessto hard-to-reachdevices.
• One person
calibration without
the need to open
the detector. Savestime and removesneed for hot work
permit.

Sensepoint XRL Technical Specifications
PHYSICAL PROPERTIESUSER INTERFACEDIMENSIONSVISUAL INDICATORWEIGHT
CASING MATERIAL
INGRESS PROTECTION
RATING
LIFETIME

118 x 159 x 93 mm( 4.4 x 6.2 x 3.6 in )1400 g (3.1 lb)
Aluminum alloy LM20 (charcoal or yellow)
IP66, NEMA 4X
10 years (excludes sensor)

AVAILABLE SENSORSFLAMMABLE, TOXIC GASESAND OXYGEN RANGESWIRELESS INTERFACE• Combustible: O to 100 % LEL (adjustablebetween 20 and 100% LEL, Factory calibratedto Methane)• O₂: 0 to 25% vol• CO: O to 300 ppm (adjustable between50 and 1000 ppm)
• H₂: O to 1000 ppm• H₂S Low Range: 0 to 50 ppm (adjustable between10 and 50 ppm)
• H₂S High Range: 0 to 100 ppm (adjustablebetween 50 and 200 ppm)

OPERATING ENVIRONMENTOPERATING TEMPERATURE
STORAGE TEMPERATURE
HUMIDITY
ATMOSPHERIC PRESSURE

AC INPUT VOLTAGE
INRUSH CURRENT

ELECTRICAL SAFETY

24 V DC†
24 V AC‡, 50/60 Hz
850 mAEMC
RADIO

OUTPUT
ANALOG OUTPUTDIGITAL OUTPUT

HAZARDOUS AREA

0 to 22 mA
Modbus RTU

MAXIMUM POWER CONSUMPTIONmA VERSIONSMODBUS VERSIONS< 1.5 W (toxic), < 2.6 W (flammable)< 1.0 W (toxic), < 2.0 W (flammable)

CONNECTION
TYPE−40 to 65 °C (−40 to 140 °F)
0 to 30 °C (32 to 86 °F)
0 to 99% (non-condensing)
90 to 110 kPa

CERTIFICATIONSPOWER SUPPLYDC INPUT VOLTAGE

Multi-colour LED light ring
• Flashing green: Normal§• Flashing red: Alarm• Flashing green and yellow: Warning• Flashing yellow: Fault• Solid yellow: Inhibited• Flashing blue: Bluetooth pairing in progress• Solid blue: Bluetooth connection establishedBluetooth 4.0 (Bluetooth Low Energy). Dedicatedmobile app, enabling wireless configuration andmaintenance. Connect up to 10 m (30 ft) away(mobile device dependent). Use a compatible
smartphone or other mobile device running Android
4.3 or above.

Pluggable rising clamp style,
0.5 to 2.5 mm2, 20 to 13 AWG† mA versions: 11 to 32 VDC, Modbus versions: 9 to 32 VDC‡ All versions: 20 to 27 VAC

GAS PERFORMANCE§LED behavior in normal condition can be changed by the user: green confidence flash, solidgreen or off.

For more information

Asia Pacific, India

www.honeywellanalytics.com

Honeywell Analytics Asia PacificNorth Asia Tel: +82 (0) 2 6909 0300
South East Asia Tel: +65 6580 3662
India Tel: +91 124 4752700
China Tel: +86 10 5885 8788-3000

Europe, Middle East, AfricaLife Safety Distribution GmbH
Tel: 00800 333 222 44 (Freephone number)
Tel: +41 44 943 4380 (Alternative number)
Middle East Tel: +971 4 450 5800 (Fixed gas detection)
Middle East Tel: +971 4 450 5852 (Portable gasdetection)

Americas
Honeywell Analytics Distribution Inc.
Tel: +1 847 955 8200Toll free: +1 800 538 0363
RAE Systems by Honeywell
Phone: 408.952.8200
Toll Free: 1.888.723.4800

EN/IEC/UL 61010-1
CSA C22.2 No. 61010-1-12
EN 50270:2015
RED, FCC, IC• ATEXII 2 GD
Ex db IIC T6 Gb
Ex tb IIIC T85 °C Db
Tamb −40 to +65 °C• IECExEx db IIC T6 Gb
Ex tb IIIC T85 °C Db
Tamb −40 to +65 °C• cULusClass I, Division 1 & 2, Groups B, C and D
Class II, Division 1 & 2, Groups E, F and G
Class I, Zone 1, AEx db IIC T6Zone 21, AEx tb IIIC T85°C, IP6X
Ex db IIC T6 GbX
Ex tb IIIC T85°C DbX
Tamb −40 to +65 °C, Temp Code T6
CSA C22.2 No.152-M1984, UL 2075, AS 1668.2

www.honeywell.com
DS_01178 | Rev. 01 | 08/2017© 2017 Honeywell International Inc.