5 A with power boost
CBscheme

SL5.100

IEC60950

Data sheet

UL508 LISTED
IND. CONT. EQ.
18 WM, 60°C

••••
••

Input: AC 230V / 115V
Output: 24V / 5A
Power boost up to 6A
High overload current, no switch-off
Quasi-Wide-Range Input
Robust mechanics and EMC

Input
Input voltage

AC100-120/200-240 V (switchable), 47-63 Hz(85-132 VAC / 176-264 VAC, 210-375 VDC,
see also „Output: Continuous Loading“)< 2.6 A (switch in 115V position)< 1.4 A (switch in 230V position)• DCin at open output typ. 5 mA (preserves battery sources)
Inrush current

EMC andLow Volt.
DirectiveOutput

Quasi-Wide-Range Input: With the switch in the 230V position the power-supply unit operates at low and moderate loads (until 3 A) at any input voltage between 95 and 264 V AC (see ’Output’ below).
Note: At DC input, always leave the switch in the 230V position
Input current

UL60950 E137006
CUL/CSA-C22.2
No 60950

typ. 15 A at 264 V AC and cold start

Output voltage

24 V DC +5% –1%Output noise
suppression

Radiated EMI values below EN 61000-6-3, evenwhen using long, unscreened output cables.

Ambient temperature
range Tamb

Operation: -10°C...+70°C (>60°C: Derating)Storage: -25°C...+85°C

Continuous loading

SwitchAC/DCinIout(at Tamb= -10°C...+60°C, 230V
176-264 V
ACin 5 A / 6 A *convection cooling), see
95-176 V
ACin 3 A
also diagram overleaf.
210-375 V
DCin 5 A / 6 A *For start at Tamb< 0°C and150-210 V
DCin 3 A
low input voltage, pleasecontact PULS.
100-150 V
DCin 2 A
Output is protected
115V
85-132 VACin 5 A / 6 A *against short circuit,* short-term 6 A (< 1 min), at 45°C or forced coolingopen circuit and overload
even continuous

To be fused with a 10A, B-type 'circuit-breaker' switch based on the usual thermomagn. overload sensing principle (used anyway to fuse the input lines). In addition, the unit contains an internal fuse (not accessible)

Derating

typ. 3 W/K

EN 61000-3-2 (harmonic current emissions) is fulfilled

Voltage regulation

better than 2% Vout overall

TransienthandlingTransient resistance acc. to VDE 0160 / W2
(750 V / 1.3 ms), for all load conditions.

Ripple / Noise< 50 mVPP, (20 MHz bandw., 50 Ω measurem.)Hold up time

> 37 ms at 196 VAC, 24 V / 5 A(see Diagram overleaf)

Overvolt. protection

typ. 29 V

Parallel operation

yes; current sharing available on request

Power back immunity

26 V

Front panel indicator

Green LED, goes out at Vout <18V

Efficiency, Reliability etc.*
Efficiency

typ. 90 %Lossestyp. 13,3 W(230 VAC, 24 V / 5 A)

MTBF

520,000 h acc. to Siemensnorm SN 29500(24 V/5 A, 230 VAC, Tamb = +40 °C)(230 VAC, 24 V / 5 A)

Life cycle (electrolytics) The unit exclusively uses longlife electrolytics,specified for +105°C (cf. ’The SilverLine’, p.2).

Construction / Mechanics*
Housing dimensions and Weight
64 mm x 124 mm x 102 mm (+ DIN rail)• WxHxD
above/below 25 mm recommended• Free space forleft/right 15 mm recommended
ventilation
620 g• Weight
Design advantages:• All connection blocks are easy to reach as mounted at the front panel.
• Input and output are strictly apart from each other and so cannot bemixed up (Input below, output above).
*For further information see data sheets „The SilverLine“, „SilverLine Family
Branches“ and mechanics data sheet

sl5e100 / 041210(at Tamb=+60°C...+70°C)

Start / Overload Behaviour
Startup delay

typ. 0.1 s

Rise timeca. 5-20 ms, depending on load

Overload Behaviour• Special PULS Overload Design (seediagram overleaf)• 20% power boost– no disconnection, no hiccup if overloaded– high overload current (up to 1.9 INom), Voutis gradually reduced with increasing current.
– 6A short-term, at 45°C or forced coolingeven continuous

Advantages:• High short-circuit current, giving large ’start-up window’: unit starts
reliably even with awkward loads (DC-DC converters, motors).
• No ’sticking’ such as can occur with fold-back characteristics• Secondary fuses operate reliably

Order information
Order numberDescription

SL5.100
SLR5.100
SLS5.100
SLZ01(Basic version*)(N+1 redundancy*)(Safety Cover*)Screw mounting set, two needed per unit
1/2

Data sheet
6DCin28

Tamb = 60°C / 45°C / 25°C/ 0 °C424220210

100

Output current Iout [A]Output characteristic (min.)Output voltage Vout [V]Output current Iout [A]Output Current over Input Voltage (min.)200300
Input voltage VDCin [V]

6375

400

ACinswitch at 115V

416128switch at
230V

42095
85

1001321760264

200300
Input voltage VACin [V]

24400

68
Output current Iout [A]

10121491

91

8989
Efficiency [%]Efficiency [%]Efficiency (min.)

8785
85V AC
115V AC
132V AC

83

8785
176V AC
230V AC
264V AC83
8181
1234Output current Iout [A]

5617234567Output current Iout [A]Hold-up time (min.)100

1009090

Iout=3 A80

Hold-up time [ms]Hold-up time [ms]

70

60
50

Iout=5 A

403020DCin

10switch pos.
115V

80

Iout=2,0 A

70

Iout=3 A

Iout=5 A

60
50

Iout=2,0 A
Iout=3 A

switch pos.
230V
Iout=5 A

40
3020ACin

100090

130

170

210

250

290

Input voltage VDCin [V]33090120150
180
Input voltage VACin [V]210240For further information, especially about• EMC• Connections• Safety, Approvals• Mechanics und Mounting,see page 2 of the „The SilverLine“ data sheet.
For detailed dimensions
see SilverLine mechanics data sheet SL2.5/ SL5/ SL10
Unless otherwise stated, specifications are valid for AC 230V input voltage, +25°C ambient temperature, and 5 min. run-in time. They are subject to change without prior notice.

Your partner in power supply:

EuropeanPower Supply
Manufacturers
AssociationBayerns Best 50
Czech 100 Best
EuropeÕs 500

PULS GmbH
Arabellastraße 15
D-81925 MünchenTel.: +49 89 9278-0
Fax: +49 89 9278-199
www.puls-power.com

2/2sl5e100 / 041210

Mechanics

Data sheet

SL2.5/ SL5/ SL10
• Innovative DIN-Rail mount, unit
holds even at vibration or lateralpressure• Clearly arranged and user oriented• Large, robust screw terminals• Sealed metal housing• Fine ventilating gridSide view SL2.5

Front view SL2.5

Construction / Mechanics

Connections

Housing dimensions and Weight
Free space for ventilation
Unit
W x H x D [mm] weightleft
above/below right• SL2.5
49 x 124 x 102 460 g
0 mm 25 mm each 10 mm• SL5.10x 64 x 124 x 102 620 g
15 mm 25 mm each 15 mm• SL5.300 73 x 124 x 117 730 g
15 mm 50 mm each 15 mm• SL10120 x 124 x 102 980 g
15 mm 25 mm each 15 mm
Overall depth = depth value as mentioned + DIN rail depth

Connections• Input/Output• Current handling
capacity• GridScrew terminals, connector size range:solid 0.5- 6 mm2 / flexible 0.5- 4 mm230 A per output
Two connectors per output, 9 mm distance
between adjacent connectors

Designadvantages:• All connection blocks are easy to reach as
mounted at the the front panel.
• Input and output are strictly apart fromeach other and so cannot be mixed up

Robust metal housing withfine ventilat. grid ( 3,5 mm, IP20), to keep out small parts (e.g. screws)
Mountingon DIN-Rail (TS35/7.5 or TS35/15, 1...1.5 mm thick), thus
• Simple snap-on system• Sits safely and firmly on the DIN-Rail• No tools required to remove
or backplane-mounted(two optional screw mounting sets SLZ01 required)sledrw1 / 040114

Bottom view SL2.5

Order information
Order numberDescription

SL2.100
SL2.103SL5.100
SL5.102
SL5.105
SL5.300
SL10.100 and SL10.105
SL10.101
SLZ01

24V/2.5A
12-15V/40W
24V/5A
24-28V/120W
24-28V/120W
24-28V/120W, 3AC400-500V input
24-28V/240W
48-56V/240W
Screw mounting set, two needed per unit
1/2

Data sheet

All views SL5.300
120

Bottom view
SL10 SL5.10x

Side view and front view
SL10, SL5.10x

his ’mechanics data sheet’ exclusively deals with the mechanical properties of the product. For further information (especially concerning electrical properties), please refer to the generic datasheet of the SL2.5, SL5 and SL10 and to the basic data sheet „The SilverLine“ dealing with common features of all SilverLine units. This data sheet is subject to change without prior notice.

Your partner in power supply:

EuropeanPower Supply
Manufacturers
AssociationBayerns Best 50
Czech 100 Best
EuropeÕs 500

PULS GmbH
Arabellastraße 15
D-81925 München
Tel.: +49 89 9278-0
Fax: +49 89 9278-199
www.puls-power.com

2/2

sledrw1 / 040114