POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

POE POWER SUPPLY
•
•
•
•
•
•
•
•

AC 100-240V Wide-range input
PULS Power Supply integrated
Width only 77mm
8x 30W ports (acc.to IEEE 802.3at)
Data transfer rate 1000Mbps
Temperature range -25°C to +70°C
Plug & Play installation and DIN rail mounting
3 Year warranty

PRODUCT DESCRIPTIONSHORT-FORM DATAThe POE.8AT-AC1 is a DIN rail mountable Power over
Ethernet (PoE) injector which comes with an integrated
PULS Power Supply of the highly reliable DIMENSION
product family. It can inject full 30W to each of 8
individual PoE channels (according to IEEE 802.3at) via
RJ45 Ethernet ports, so no power sharing is limiting theuse of single channels. The device can supply powered
devices PD of type1 and type2 (PoE+).

AC Input voltage
range
DC Output voltage
range

AC 100-240V

Suitable for TN-, TT- andIT mains networks

48 – 56Vdc

Factory setting 53V (ForType 2 PoE+ the output
voltage must be above
50V)

Output power

8x 30W (PoE+)
8x 15.4W (PoE)
0.63A (PoE+)
0.33A (PoE)-25°C to +60°C ambient-25°C to +70°C ambient-25°C to +60°C ambient-25°C to +70°C ambient

93.1%
17.8W
-25°C to +70°C
77x128x117mm
940g / 2.1 lb

At 230Vac
At 230Vac

Output current
limitation per

channelEfficiency
LossesTemperature range
Size (wxhxd)
WeightORDER NUMBERS

Without DIN rail

MAIN APPROVALSPoE Power Supply

POE.8AT-AC1

Mechanical Accessory

ZM10.WALL
Wall/panel mount bracket

For details and the complete approval list, see chapter 19.

UL 61010-2-201(planned)

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

1/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

INDEX
Page
1. Intended Use .......................................................3
2. Installation Instructions ......................................3
3. AC-Input...............................................................5
4. DC-Input...............................................................6
5. Input Inrush Current ...........................................7
6. Output .................................................................7
7. Hold-up Time .......................................................8
8. DC-OK Relay Contact ..........................................99. Efficiency and Power Losses..............................10
10. Lifetime Expectancy ..........................................10
11. Functional Diagram ...........................................10
12. Terminals and Wiring ........................................11
13. Front Side and User Elements ...........................12
14. EMC ....................................................................13Page
15. Environment ..................................................... 14
16. Protection Features .......................................... 15
17. Safety Features ................................................. 15
18. Dielectric Strength ............................................ 16
19. Approved, Fulfilled or Tested Standards ......... 17
20. Regulatory Product Compliance ...................... 17
21. Physical Dimensions and Weight ..................... 18
22. Accessories ........................................................ 19
22.1. ZM10.WALL–Wall/Panel Mount Bracket . 19
23. Application Notes ............................................. 20
23.1. External Input Protection ......................... 20
23.2. Operation on Two Phases ........................ 20

The information given in this document is correct to the best of our knowledge and experience at the time of
publication. If not expressly agreed otherwise, this information does not represent a warranty in the legal sense of theword. As the state of our knowledge and experience is constantly changing, the information in this data sheet issubject to revision. We therefore kindly ask you to always use the latest issue of this document (available underwww.pulspower.com).
No part of this document may be reproduced or utilized in any form without our prior permission in writing.

TERMINOLOGY AND ABREVIATIONSPE andsymbolEarth, GroundPE is the abbreviation for Protective Earth and has the same meaning as the symbol.

This document uses the term “earth” which is the same as the U.S. term “ground”.

t.b.d.

To be defined, value or description will follow later.

AC 230V

A figure displayed with the AC or DC before the value represents a nominal voltage withstandard tolerances (usually ±15%) included.
E.g.: DC 12V describes a 12V battery disregarding whether it is full (13.7V) or flat (10V)

230VacA figure with the unit (Vac) at the end is a momentary figure without any additional
tolerances included.

50Hz vs. 60Hz

As long as not otherwise stated, AC 100V and AC 230V parameters are valid at 50Hz mains
frequency. AC 120V parameters are valid for 60Hz mains frequency.

may

A key word indicating flexibility of choice with no implied preference.

shall

A key word indicating a mandatory requirement.

shouldA key word indicating flexibility of choice with a strongly preferred implementation.

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

2/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

1. INTENDED USEThis device is designed for installation in an enclosure and is intended for commercial use, such as in industrial control,
process control, monitoring and measurement equipment or the like.
The device is suitable for indoor applications. Outdoor applications are also allowed as long as all requirements
specified in this manual (enclosure, controlled environment, condensation, ...) are met.
Do not use this device in equipment, where malfunctioning may cause severe personal injury or threaten human life
without additional appropriate safety devices, that are suited for the end-application. If this device is used in a manner
outside of its specification, the protection provided by the device may be impaired.

2. INSTALLATION INSTRUCTIONSWARNING

Risk of electrical shock, fire, personal injury or death.

- Turn power off before working on the device and protect against inadvertent re-powering.
- Do not open, modify or repair the device.
- Use caution to prevent any foreign objects from entering into the housing.
- Do not use in wet locations or in areas where moisture or condensation can be expected.
- Do not touch during power-on, and immediately after power-off. Hot surface may cause burns.
Obey the following installation instructions:This device may only be installed and put into operation by qualified personnel.
This device does not contain serviceable parts.
If damage or malfunction should occur during installation or operation, immediately turn power off and send unit to
the factory for inspection.
Install device in an enclosure providing protection against electrical, mechanical and fire hazards. Install the device onto
a DIN rail according to EN 60715 with the input terminals on the bottom of the device.
Make sure that the wiring is correct by following all local and national codes. Use appropriate copper cables that aredesigned for a minimum operating temperature of 60°C for ambient temperatures up to +45°C, 75°C for ambient
temperatures up to +60°C and 90°C for ambient temperatures up to +70°C. Ensure that all strands of a stranded wire
enter the terminal connection. Use ferrules for wires on the input terminals. Unused screw terminals should be securely
tightened. Use shielded twisted pair Ethernet cables specified for usage in IEEE 802.3at.
The device is designed for pollution degree 2 areas in controlled environments. No condensation or frost is allowed.
The enclosure of the device provides a degree of protection of IP20. The enclosure does not provide protection against
spilled liquids.
The isolation of the device is designed to withstand impulse voltages of overvoltage category III according toIEC 60664-1.
The device is designed as “Class of Protection I” equipment according to IEC 61140. Do not use without a proper PE(Protective Earth) connection.
The device is suitable to be supplied from TN, TT or IT mains networks. The continuous voltage between the input
terminal and the PE potential must not exceed 264Vac.
The input can also be powered from batteries or similar DC sources. The continuous voltage between the supply
voltage and the PE/ground potential must not exceed 180Vdc.
A disconnecting means shall be provided for the input of the device.
The device is designed for convection cooling and does not require an external fan. Do not obstruct airflow and do notcover ventilation grid!
The device is designed for altitudes up to 2000m (6560ft).

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

3/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT
Keep the following minimum installation clearances: 40mm on top, 20mm on the bottom, 5mm left and right side.
Increase the 5mm to 15mm in case the adjacent device is a heat source. When the device is permanently loaded withless than 50%, the 5mm can be reduced to zero.
The device is designed, tested and approved for branch circuits up to 20A without additional protection device. If an
external fuse is utilized, do not use circuit breakers smaller than 6A B- or C-Characteristic to avoid a nuisance tripping of
the circuit breaker.
The maximum surrounding air temperature is +70°C (+158°F). The operational temperature is the same as the ambientor surrounding air temperature and is defined 2cm below the device.
The device is designed to operate in areas between 5% and 95% relative humidity.
Do not plug or unplug the device as long as input voltage is present.
Do not unplug the input connectors more often than 20 times in total.

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

4/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

3. AC-INPUT
AC inputnom.

AC 100-240V

Suitable for TN-, TT- and IT mains networks

Allowed voltage L or N to earthmax.

264VacContinuous according to IEC 62477-1

Input frequency

nom.

50–60Hz±6%

Turn-on voltage

typ.

80Vac

Steady-state value, see Fig. 3-1

Shut-down voltage

typ.

70Vac

Steady-state value, see Fig. 3-1

typ.

55Vac

Dynamic value for maximal 250ms

AC 100VAC 120V

AC 230V

2.62A

2.21A

1.16A

At 8x 30W PoE

Input current

typ.

Power factor

typ.

0.99

0.99

0.97

At 8x 30W PoE

Turn-on time**)

typ.

763ms

753ms

700ms

Switch on at Input zero transition

External input protection

See recommendations in chapter 23.1*)*) The power factor is the ratio of the true (or real) power to the apparent power in an AC circuit.
**) Including device detection

Fig. 3-2 Input current vs. output current at
53V output voltage

Fig. 3-1 Input voltage range

Rated
input range

POUT

max.
500ms

Input Current, typ.

3A

1.5

b)

1.0

VIN
90V

a)

a) 100Vacb) 120Vacc) 230Vac

2.0
Turn-onShut-down

2.5

264V 300Vac

c)

0.5
0

Output Current

0

30

60

90

120

150 180

210 240W

Fig. 3-3 Power factor vs. output current at
53V output voltage
Power Factor, typ.

1.00

a)

b)

0.95
0.90

c)
a) 100Vacb) 120Vacc) 230Vac

0.85
0.80
0.75
30

Output voltage

60

90 120150 180 210 240W

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

5/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

4. DC-INPUT
DC inputnom.

DC 110-150V±20%

DC input range

min.

88-180Vdc

Continuous operation,

DC input current

typ.

2.35A

At 110Vdc

Allowed voltage L/N to
Earth

max.

Turn-on voltage

typ.

80Vdc

Steady state value

Shut-down voltage

typ.

70Vdc

Steady state value

typ.

55Vdc

Dynamic value for maximal 250ms

External input protection

180VdcContinuous, according to IEC 62477-1

See recommendations in chapter 23.1

Instructions for DC use:a) Use a battery or a similar DC source. A supply from the intermediate DC-bus of a frequency converter is notrecommended and can cause a malfunction or damage the unit.
b) Connect +pole to L and –pole to N.
c) Connect the PE terminal to an earth wire or to the machine ground.
Fig. 4-1 Wiring for DC Input

Battery+

Power Supply
AC
L
N
PE

-

+
-

Load

DC

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

6/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

5. INPUT INRUSH CURRENT
An active inrush limitation circuit (NTCs, which are bypassed by a relay contact) limits the input inrush current afterturn-on of the input voltage.
The charging current into EMI suppression capacitors is disregarded in the first microseconds after switch-on.

Inrush current

Inrush energy

AC 100VAC 120V

AC 230Vmax.

11Apeak

7Apeak

11Apeak

At 40°C, cold start

typ.

9Apeak

6Apeak

6ApeakAt 25°C, cold start

typ.

9Apeak

6Apeak9ApeakAt 40°C, cold startmax.

0.1A²s

0.1A²s

0.4A²sAt 40°C, cold startFig. 5-1 Typical turn-on behavior at nominal
load, 120Vac input and 25°C ambient

Fig. 5-2 Typical turn-on behavior at nominal
load, 230Vac input and 25°C ambient

6. OUTPUT
Output voltage

nom.

53V

Adjustment rangemin.

48-56V

Guaranteed value

max.

58.0V

This is the maximum output voltage which canoccur at the clockwise end position of thepotentiometer due to tolerances. It is not aguaranteed value which can be achieved.

Factory settings

typ.

53V

At full load and cold unit

Line regulation

max.

10mV

Between 85 and 264Vac

Load regulation

max.

50mV

Between 0 and 4.5A, static value

Ripple and noise voltage

max.

50mVpp

Bandwidth 20Hz to 20MHz, 50Ohm

RJ45 Output channels

8x 30W (PoE+)
8x 15.4W (PoE)-25°C to 60°C ambient-25°C to 70°C ambient

Output current limitation

0.63A (PoE+)-25°C to 60°C ambient

0.33A (PoE)-25°C to 70°C ambientJan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

7/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

7. HOLD-UP TIME
Hold-up TimeAC 100VAC 120V

AC 230V

min.

50ms

50ms

50ms

4x 30W PoE

min.

26ms

26ms

26ms

8x 30W PoE

Fig. 7-1 Hold-up time vs. input voltage

Hold-up Time

80ms
70
60
50
40
30
20
10
0

Fig. 7-2 Shut-down behavior, definitionsa) 53V 120W b) 53V 240W

Zero Transition
Input
Voltageab

Hold-up Time

Input Voltage

90

120

155

190

- 5%

OutputVoltage

230VacJan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

8/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

8. DC-OK RELAY CONTACT
This feature monitors the output voltage on the output terminals of a running power supply.
Contact closes

As soon as the output voltage reaches typ. 90% of the adjusted output voltage level.

Contact opens

As soon as the output voltage dips more than 10% below the adjusted output voltage.
Short dips will be extended to a signal length of 100ms. Dips shorter than 1ms will beignored.

Switching hysteresis

typ. 2V

Contact ratings

Maximal 60Vdc 0.3A, 30Vdc 1A, 30Vac 0.5A, resistive load
Minimal permissible load: 1mA at 5Vdc

Isolation voltage

See dielectric strength table in section 18.

WARNING
In order to fulfill the IEEE 802.3at requirements, external equipment and wiring connected to the DC-OK contact needto have a minimum isolation strength of 1500Vac to ground.

Fig. 8-1 DC-OK relay contact behavior
VOUT = VADJ
10%

<
1ms

open

closed>1ms

0.9* VADJ

100ms

open

closedJan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

9/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

9. EFFICIENCY AND POWER LOSSESAC 100VAC 120V

AC 230V

Efficiency

typ.

89.1%

91.5%

93.1%

at 8x 30W output

Power losses

typ.

29.4W

22.3W

17.8W

at 8x 30W output

10. LIFETIME EXPECTANCYThe Lifetime expectancy shown in the table indicates the minimum operating hours (service life) and is determined by
the lifetime expectancy of the built-in electrolytic capacitors. Lifetime expectancy is specified in operational hours and is
calculated according to the capacitor’s manufacturer specification. The manufacturer of the electrolytic capacitors only
guarantees a maximum life of up to 15 years (131 400h). Any number exceeding this value is a calculated theoretical
lifetime which can be used to compare devices.

Lifetime expectancy

AC 100VAC 120V

AC 230V

141 000h

158 000h

188 000h

At 53V, 8x 15.4W and 40°C

399 000h

446 000h

531 000h

At 53V, 8x 15.4W and 25°C

63 000h77 000h

120 000h

At 53V, 8x 30W and 40°C

178 000h

219 000h

338 000h

At 53V, 8x 30W and 25°C

11. FUNCTIONAL DIAGRAM
Fig. 11-1 Functional diagram
Ch1

Ch1
Ch2
Ch3 .
..
..
.
Ch8
Data
Input
Channels

L
N

Ch2

PoE
Power Injector

Power
Conditioning

Input Fuse
Input Filter
Input Rectifier
Inrush Current Limiter

PFC
Converter

..
.

PoE
OutputChannels

OutputFilterPower
Converter

OutputVoltage
Regulator
TemperatureShut-down

OutputPower
Manager

OutputOverVoltage
Protection

Ch3
..
.
Ch8

OutputVoltage
Monitor

DC-ok
Relay

VOUT

DC-ok
LED
DC-ok
Contact

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

10/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

12. TERMINALS AND WIRING
Input

DC-OK-Signal

Type

Plug connector with screw
terminals

Plug connector with screw terminals

Solid wire

max. 4mm2

max. 1.5mm2

Stranded wire

max. 2.5mm2

max. 1.5mm2

American Wire Gauge

AWG 20-12

AWG 26-14

Max. wire diameter (including ferrules)

2.4mm

1.8mm

Recommended tightening torquemax. 0.5nm, 4.5lb-in

max. 0.8nm, 7lb-in

Wire stripping length

7mm / 0.28inch

6mm / 0.25inch

Screwdriver

3.5mm slotted or cross-head No 2

3.5mm slotted

Do not unplug the connectors
more often than 20 times in total

Do not unplug the connectors more
often than 20 times in total

Instructions for wiring:1) Use appropriate copper cables that are designed for minimum operating temperatures of:
60°C for ambient up to 45°C, 75°C for ambient up to 60°C and 90°C for ambient up to 70°C minimum.
2) Follow national installation codes and installation regulations!
3) Ensure that all strands of a stranded wire enter the terminal connection!
4) Unused terminal compartments should be securely tightened.
5)

Ferrules are allowed and recommended.

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

11/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

13. FRONT SIDE AND USER ELEMENTS
Fig. 13-1
Front sideA

Power input terminal

Hot swap connector

B

Ethernet inputs

8x RJ45 jacks

C

Ethernet/PoE outputs

8x RJ45 jacks

D

Output voltage
potentiometer

Factory setting 53V

E

DC-OK LED (green)

ON when the output
voltage is >90% of theadjusted output voltage

F

DC-OK relay contact

Hot swap connector

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

12/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

14. EMCThe power supply is suitable for applications in industrial environment as well as in residential, commercial and lightindustry environments.
EMC Immunity

According to generic standards: EN 61000-6-1 and EN 61000-6-2 and productstandard EN 55024

Electrostatic discharge

EN 61000-4-2

Contact discharge
Air discharge

±4kV
±8kV

Criterion B
Criterion B

Electromagnetic RF field

EN 61000-4-3

80MHz-1GHz

10V/m

Criterion A

1.4GHz-2GHz

3V/m

Criterion A

2GHz-2.7GHz

1V/m

Criterion A

Fast transients (Burst)

EN 61000-4-4

AC Input lines
Data ports

±2kV
±1kV

Criterion B
Criterion B

Surge voltage on input

EN 61000-4-5

LN

±1kV

Criterion B
Criterion B

EN 61000-4-5

L; N  PE
Data lines  PE

±2kV

Surge voltage on data input lines
and PoE output lines±1kV

Criterion B

Surge voltage on DC-OK signal lines

EN 61000-4-5

DC-OK signal  PE

Conducted disturbanceEN 61000-4-6

0.15-80MHz

±1kV
10V

Criterion B
Criterion A

Power Frequency Magnet Field

EN 61000-4-8

50Hz / 60Hz

30A/m

Criterion A

Mains voltage dips

EN 61000-4-11

0% of 100Vac
40% of 100Vac
70% of 100Vac
0% of 200Vac
40% of 200Vac
70% of 200Vac

0Vac, 20ms
40Vac, 200ms
70Vac, 500ms
0Vac, 20ms
80Vac, 200ms
140Vac, 500ms

Criterion A
Criterion C
Criterion C
Criterion A
Criterion A
Criterion A

Voltage interruptions

EN 61000-4-11

0% of 200Vac (=0V)

5000msCriterion C

Criterions:
Before, during and after the test the equipment shall operate as intended, no loss of function and the output voltage
A:
must be within +/-5% range and the data rate within 95% and 100%.
B:

Before, during and after the test the equipment shall operate as intended, no loss of function or loss of data links shalloccur. After the test there shall be no degradation of performance.

C:

Temporary loss of PoE power function is possible. PoE Power supply may shut-down and restarts by itself. No damage or
hazards will occur. The data transmission will be not interrupted.

EMC Emission

According to generic standards: EN 61000-6-3 and EN 61000-6-4 and productstandard EN 55032

Conducted emission
input lines

EN 55011, EN 55032,
FCC Part 15, CISPR 11, CISPR 32

Class B

Conducted emission
on data ports (Input and PoE
output lines)

EN 55032

Class B

Radiated emission

EN 55011, EN 55032

Class B

Harmonic input current

EN 61000-3-2Class A fulfilled

Voltage fluctuations, flicker

EN 61000-3-3

Fulfilled

This device complies with FCC Part 15 rules.
Operation is subjected to following two conditions: (1) this device may not cause harmful interference, and (2) thisdevice must accept any interference received, including interference that may cause undesired operation.
Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

13/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

Switching Frequencies
PFC converter

110kHzFixed frequency

Main converter

84kHz to 140kHz

Output load dependent

Auxiliary converter

60kHz

Fixed frequency

15. ENVIRONMENT
Operational temperature1)-25°C to +60°C (-13°F to 140°F)-25°C to +70°C (-13°F to 158°F)

Storage temperature-40°C to +85°C (-40°F to 185°F)

For storage and transportation

Humidity

5 to 95% r.h.

According to IEC 60068-2-30
Do not energize while condensation ispresent

Over-voltage categoryIII

According to IEC 60664-1 for altitudes up to
2000m

Audible noise

Some audible noise may be emitted from the power supply during no load, overload or
short circuit.

1)

PoE+ application (30W per channel)
PoE application (15.4W per channel)

Operational temperature is the same as the ambient or surrounding temperature and is defined as the air temperature 2cm below the unit.

Fig. 15-1 Output power vs. Ambient temp.

Allowed output power

8x 30WA

8x 15.4W

B

0A
-25

A: PoE+ Applications
B: PoE Applications

0

60 70°C
Ambient temperatureJan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

14/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

16. PROTECTION FEATURES
Output protection

Electronically protected against overload, no-load and short-circuits. In case of aprotection event, audible noise may occur.

Output over-voltage protection

Typ. 58.5Vdc
Max. 60Vdc

In case of an internal power supply defect, a redundantcircuit limits the maximum output voltage. The output
shuts down and automatically attempts to restart.

Degree of protection

IP 20

EN/IEC 60529

Penetration protection> 4mm

E.g. screws, small parts

Over-temperature protection

Yes

Output shut-down with automatic restart.
The temperature sensor is installed on critical components
inside the unit and turns the unit off in safety criticalsituations (e.g. derating requirements not observed, highambient temperature, ventilation obstructed. There is nocorrelation between the operating temperature and turnoff temperature since this is dependent on input voltage,load and installation methods.

Input transient protection

MOV(Metal Oxide Varistor)

For protection values see chapter 14 (EMC).

Internal input fuse

IncludedNot user replaceable slow-blow high-braking capacity fuse

17. SAFETY FEATURES
Input / output separation

Double or reinforced galvanic isolation
SELV

IEC 60950-1

PELV

IEC/EN 60204-1, EN 62477-1, IEC 60364-4-41

Class of protectionI

PE (Protective Earth) connection required

Isolation resistance> 500MOhm

At delivered condition between input and output,
measured with 500Vdc> 500MOhm

At delivered condition between input and PE, measured
with 500Vdc> 500MOhm

At delivered condition between output and PE, measured
with 500Vdc> 500MOhm

At delivered condition between output and DC-OK
contacts, measured with 500Vdc

PE resistance< 0.1Ohm

Resistance between PE terminal and the housing in thearea of the DIN rail mounting bracket.

Touch current (leakage current)

typ. 0.14mA / 0.36mA

At 100Vac, 50Hz, TN-,TT-mains / IT-mains

typ. 0.20mA / 0.50mA

At 120Vac, 60Hz, TN-,TT-mains / IT-mains

typ. 0.33mA / 0.86mA

At 230Vac, 50Hz, TN-,TT-mains / IT-mains

max. 0.18mA / 0.43mA

At 110Vac, 50Hz, TN-,TT-mains / IT-mains

max. 0.26mA / 0.61mA

At 132Vac, 60Hz, TN-,TT-mains / IT-mains

max. 0.44mA / 1.05mA

At 264Vac, 50Hz, TN-,TT-mains / IT-mains

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

15/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

18. DIELECTRIC STRENGTH
The output voltage is floating and has no ohmic connection to the ground. Type and factory tests are conducted by the
manufacturer. Field tests may be conducted in the field using the appropriate test equipment which applies the voltage
with a slow ramp (2s up and 2s down). Connect all input-terminals together as well as all output poles before
conducting the test. When testing, set the cut-off current settings to the value in the table below.
Fig. 18-1 Dielectric strength

DC-okPower In

L
N

B

*)

D

60s

2500Vac

4000Vac

1500Vac

500Vac14

Factory test

5s

2500Vac

2500Vac1350Vac

500VacField test

5s

2000Vac

2000Vac

1000Vac

500Vac> 10mA> 20mA> 60mA> 5mA

Ethernet/PoE

Earth, PE

C

Type test

D

C

B

13

B
A

A

Cut-off current
settingCB*) When testing input to DC-OK ensure that the max. voltage between DC-OK and the Ethernet Ports is not exceeded (column D). We recommend
connecting DC-OK pins and all Ethernet leads together when performing the test.

WARNING
In order to fulfill the IEEE 802.3at requirements, external equipment and wiring connected to the DC-OK contact needto have a minimum isolation strength of 1500Vac to ground.

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

16/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

19. APPROVED, FULFILLED OR TESTED STANDARDSUL 61010(planned)

UL Certificate
UL 61010-2-201 Electrical Equipment for Measurement, Control
and Laboratory Use - Particular requirements for control
equipment
Applicable for US and Canada
E-File: E198865

IEC 62368(planned)

CB Scheme Certificate
IEC 62368-1 Audio/video, information and communication
technology equipment - Safety requirements
Output safety level: ES1

IEC 61010(planned)

CB Scheme Certificate
IEC 61010-2-201 Electrical Equipment for Measurement, Control
and Laboratory Use - Particular requirements for control
equipment

20. REGULATORY PRODUCT COMPLIANCE
EU Declaration of Conformity

The CE mark indicates conformance with the- EMC directive- Low-voltage directive- RoHS directive

WEEE Regulation

Manufacturer's Declaration
EU Regulation on Waste Electrical and Electronic Equipment
Registered as business to business (B2B) products.

REACH Directive

Manufacturer's Statement
EU-Directive regarding the Registration, Evaluation,
Authorization and Restriction of Chemicals

EAC TR Registration

EAC Certificate
EAC EurAsian Conformity - Registration Russia, Kazakhstan
and Belarus
8504408200, 8504409000

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

17/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

21. PHYSICAL DIMENSIONS AND WEIGHT
Width

77mm

Height128mm 5.06”

3.03”

Depth

117mm 4.61’’
The DIN rail depth must be added to the unit depth to calculate the total required
installation depth.

Weight940g / 2.1lb

DIN rail

Use 35mm DIN rails according to EN 60715 or EN 50022 with a height of 7.5 or 15mm.

Housing material

Body: Aluminium alloy
Cover: Zinc-plated steel

Installation clearances

See chapter 2

Fig. 21-1
Front viewFig. 21-2
Side viewAll dimensions in mm

All dimensions in mm

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

18/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

22. ACCESSORIES
22.1. ZM10.WALL–WALL/PANEL MOUNT BRACKETThis bracket is used to mount the devices on a wall/panel without utilizing a DIN rail. The bracket can be mounted
without detaching the DIN rail brackets.
Fig. 22-1 Isometric viewFig. 22-4 Wall/panel mounting,front viewFig. 22-2 Isometric viewFig. 22-5 Hole pattern for wall
mounting

Fig. 22-3 Isometric viewFig. 22-6 Wall/panel mounting,side viewJan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

19/20

POE.8AT-AC1
53V, 8X 30W, SINGLE PHASE INPUT

23. APPLICATION NOTES
23.1. EXTERNAL INPUT PROTECTION
The unit is tested and approved for branch circuits up to 30A (UL) and 32A (IEC). An external protection is only
required if the supplying branch has an ampacity greater than this. Check also local codes and local requirements. In
some countries local regulations might apply.
If an external fuse is necessary or utilized, minimum requirements need to be considered to avoid nuisance tripping of
the circuit breaker. A minimum value of 6A B- or C-Characteristic breaker should be used.

23.2. OPERATION ON TWO PHASESThe power supply can also be used on two-phases of a three-phase-system. Such a phase-to-phase connection isPower Supply
allowed as long as the supplying voltage is below 240V+10%.

L3

CenterTap

240V +10% max.

L1

AC
L
N
PE

L2

Jan. 2022 / Rev. 0.2 DS-POE.8AT-AC1-EN
All parameters are specified at 53V, 4.5A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0GermanyDC

20/20