Kawasaki Heavy Industries, Ltd.
Kawasaki Heavy Industries, Ltd. Tokyo Head Office (KHI)
Tel: +81-3-3435-2579
Kawasaki Machine Systems, Ltd. (KMS)
Tel: +81-3-3435-2977
Kawasaki Machine Systems, Ltd. Korea Branch
Tel: +82-2-527-2201
Kawasaki Gas Turbine Asia Sdn Bhd (KGA)
Tel: +60-3-5870-0300
Kawasaki Gas Turbine Europe GmbH (KGE)
Tel: +49-6172-7363-0
Kawasaki Heavy Industries (Thailand) Co., Ltd. (KHIT)
Tel: +66-2-163-2839
Kawasaki Gas Turbine Asia Sdn Bhd Jakarta Representative OfficeTel: +62-21508-15125
Kawasaki Gas Turbine Europe GmbH, Romanian Representative OfficeTel: +40-374 645915
Kawasaki Heavy Industries Management (Shanghai), Ltd.
Tel: +86-21-3366-3100
Kawasaki Energy System Solutions (Shandong) Ltd. (KESS)

ISO 9001 / ISO14001 Certified
The Energy System Division is located at
Akashi Works in Japan. It designs and manufactures the Gas Turbine Co-generation
System, and is certified for ISO 9001, theinternational standard of quality assurance,and ISO 14001, the international standard
for environmental management.

https://global.kawasaki.com/en/energy/gasengine_gasturbine/index.html
Cat. No. KTK-0001-S Printed in Japan '23-09(71)Scan a QR codefor more detail

L30A

1

2

History and Order Record of Kawasaki Gas Turbines
History
1943
1952

Completed the first Gas Turbine engine for aircrafts in Japan
Started overhauling jet engines

1972 Started development of industrial Gas Turbine
1974 Completed first S1A-01 type : 200 kW Gas Turbine
1977 First Kawasaki Gas Turbine genset : 200 kW delivered
1979 First genset to overseas customer delivered
1984 First Kawasaki Gas Turbine Co-generation system 2x1.0 MW delivered
1985 Accumulated sales of 1,000 engines
1988 1.5 MW M1A-13 type Gas Turbine introduced
1993 5.5 MW M7A-01 type Gas Turbine introduced
1995 1.5 MW M1A-13D Dry Low NOx type Gas Turbine introduced
1999
6.5 MW M7A-02 type Gas Turbine introduced
Accumulated delivery of 5,000th engine
Experimental ceramic Gas Turbine completed and achieved the world record of
42.1% simple cycle efficiency for the 300 kW class2000 18 MW L20A type Gas Turbine introduced
2005 Start-up Akashi Works Energy Center, which comprises 24.7 MW Combined
Cycle and 7.8 MW Flexible Heat and Power Gas Turbine Power Plant
2006 7.7 MW class M7A-03 type Gas Turbine introduced
2007 Received the 100th Order of the M7A Series
2009 15ppm (NOx) M7A-03D type Gas Turbine introduced

INDEX
Introduction

1.2

History and Order Recordof Kawasaki Gas Turbines
Baseload Model

3.4
5.6

M1A Series Gas Turbine
Generator Specifications
M5A Series Gas Turbine
Generator Specifications
M7A Series Gas Turbine
Generator Specifications
L20A Series Gas Turbine
Generator Specifications
L30A Series Gas Turbine
Generator Specifications

7.8
9
10
11

2010 Accumulated sales of 10,000 engines
1.7 MW class M1A-17 type Gas Turbine introduced
2012 30 MW L30A type Gas Turbine introduced
2014 30 MW L30A Low-NOx hydrogen combustion type Gas Turbine launched
2015
Demonstration test of Low-NOx Gas Turbine using mixed hydrogen combustion system
2017
5MW M5A-01D type Gas Turbine introduced

12

Kawasaki Techno-Net

13

Installation Examples

14

Kawasaki Gas Turbine places importance on "Efficient Energy Use", "Eco-friendly" and"Reliable Product Care for Total Life Cycle" as a philosophy of our products.
To enhance this philosophy,
we have introduced a title for our products......."GREEN Gas Turbines".

Accumulated Number of Engine sales all over the world
14,00013,00012,00011,00010,0009,000
8,000

M5A-01 gas turbine received technicalawards of cogen supporting product.

7,000
6,000

Green Product Certificated were issued bypublic association.

5,000
4,000
3,000
2,000

Kawasaki Group`s Approach to SDGs

1,000
0

3

'03 '04 '05 '06 '07 '08 '09 '10 '11 '12 '13 '14 '15 '16 '17 '18 '19 '20 '21 '22
4Baseload Model

BASELOADBASELOAD
Basic Specifications
EngineEngine Series
Series

M1A
M1A GasGas Turbine
Turbine Series
Series

M5A
M5A GasGas Turbine
Turbine Series
Series

L20A Gas
Gas Turbine
Turbine Series
Series
L20A

M7A
M7A GasGas Turbine
Turbine Series
Series

L30A Gas
Gas Turbine
Turbine Series
Series
L30A

Gas
Gas Turbine
Turbine Model
Model

M1A-13A
M1A-13A

M1A-13D
M1A-13D

M1A-17
M1A-17

M1A-17D
M1A-17D

M1T-13A
M1T-13A

M1T-13D
M1T-13D

M5A-01D
M5A-01D

M7A-03
M7A-03

M7A-03D
M7A-03D

L20A-01D
L20A-01D

L30A-01D
L30A-01D

Gas
Gas Turbine
Turbine Generator
Generator Model
Model

GPB15
GPB15

GPB15DGPB15D

GPB17
GPB17

GPB17DGPB17D

GPB30
GPB30

GPB30D
GPB30DGPB50DGPB50D

GPB80
GPB80

GPB80D
GPB80DGPB180D
GPB180D

GPB300D
GPB300D

kWe
kWe

1,490
1,490

1,490
1,490

1,810
1,810

2,930
2,930

7,800
7,800

18,42018,42034,38034,38015,03015,03012,83012,83015,10015,10010,73010,73010,73010,73010,53010,530

8,870
8,870

%
%

24.2
24.2

24.0
24.0

28.1
28.1

28.1
28.1

23.8
23.8

15,24015,24010,91010,910

7,800
7,800

14,88014,88012,83012,830

2,930
2,930

kJ/kWe-hr
kJ/kWe-hr

23.6
23.6

33.0
33.0

33.6
33.6

33.6
33.6

34.2
34.2

40.6
40.6

521
521

531
531

522
522

522
522

521
521

531
531

523
523

523
523

523
523

542
542

517
517

kg/hr
x10
x1033 kg/hr

29.1
29.1

28.8
28.8

29.1
29.1

29.1
29.1

58.2
58.2

57.6
57.6

63.2
63.2

97.9
97.9

97.9
97.9

215.3
215.3

322.6
322.6

ppm
ppm

--

25
25

--

99 // 15
15

--

15
15

--

Maximum
Maximum Continuos
Continuos ElectricElectric Output
OutputHeat
Heat Rate
Rate
ThermalThermal Efficiency
Efficiency
ExhaustExhaust Gas
Gas Temperature
Temperature
ExhaustExhaust Gas
Gas Mass
Mass Flow
Flow
NOx
NOx (0(022:: 15%)
15%)

Approximate
Approximate Package
Package Dimension
Dimension (L,W,H)(L,W,H) mm
Approximate
Approximate Package
PackageWeight
Weight (dry)
(dry)

kg
x10
x1033kg

5.3
5.3 xx 1.7
1.7 xx 2.4
2.4
14
14

1,810
1,810

25
25
6.0
6.0 xx 2.4
2.4 xx 2.4
2.4

6.0
6.0 xx 1.9
1.9 xx 2.6
2.6

21
21

14
14

4,960
4,960

8.7
8.7 xx 2.4
2.4 xx 3.5
3.5
41
41

9.9
9.9 // 15
15
11
11 xx 2.6
2.6 xx 3.7
3.7
58
58

15
15

15
15

17.4
17.4 xx 3.5
3.5 xx 3.4
3.4

14.2
14.2 xx 4.5
4.5 xx 5.3
5.3

143
143

155
155

Note: Mark "D" after Gas Turbine Model stands for Dry Low Emission
Condition : ISO Rating

1. Inlet Air Temperature : 15°C
4. Fuel Type : Natural Gas (100% CH4)

2. Atmospheric Pressure : 101.3 kPa
5. LHV of Fuel : 35.9 MJ/Nm3

3. Inlet / Exhaust Pressure Losses : No Duct Loss

The Kawasaki GPB Series are designed for baseload application, in both parallel operation with grid andisland mode operation. In addition, Kawasaki GPB Series are able to be operated in co-generation service,with automatic operation capability supplying both electricity and heat (steam, hot water, direct heat)by collecting waste heat with a heat recovery system generator(HRSG), heat exchanger, or dryer, and in
Combined Cycle with a steam turbine generator.
With high total thermal efficiency, Kawasaki GPB Series are capable ofsaving customer's energy cost and contribute to protect global
environment. After Kawasaki introduced M1A gas turbine toco-generation market in 1984, Kawasaki has provided
high reliable machines, more than 11,000 units in the world.

Below is Kawasaki gas turbine features,and is furnished in all units of M1A, M5A,
M7A, L20A, and L30A gas turbines.

M7A-03

Kawasaki introduced Single Digit NOx DLE combustor with
M7A-03 gas turbine to the market in 2011.
In many countries and regions, air quality requirement are
getting so strict. This super low NOx technology matchessuch market trend.
In 2012, Kawasaki introduced the largest size gas turbine,
L30A, as a flagship model of its industrial gas turbine fleet.
Based on Kawasaki state-of-the-art technology, L30A offers
the highest efficiency of 30MW class gas turbines in the world.
In addition, Kawasaki applied modular system design whichsignificantly reduces plant down-time and engine overhaul.
L30A is able to provide a highly flexible solution for power
generation and mechanical drive application.

M5A-01 gas turbine was developed with the latest andproven technologies of Kawasaki gas turbines, and achieved
highest efficiency as well as least maintenance needs of its
class.
GPB50D utilizing M5A-01D gas turbine provides the optimal
solution for power generation and co-generation.
Its compact package design is also perfect for renewal ofexisting facilities.

L30A-01

1. Self-developed Gas Turbine Fully Made in Japan
Very high quality and reliable various lineup with worldwide installation record.
2. World Highest-Class Efficiency
Kawasaki is proud of the highest efficiency achieved by its own technology.
3. Eco-Friendly
Kawasaki has developed the lowest NOx emission DLE (Dry Low Emission) combustor. With high total
thermal efficiency, Kawasaki gas turbine reduces environmental burden.
4. Fuel Flexibility
Besides natural gas, other fuels such as LNG, off-gas, Kerosene, and diesel oil can be selected as fuel.
5. Reliable After-Service
Reliable after service system is available, which satisfies customer's requirement with on-site engine
exchange program and parts supply system supported by well-experienced service persons.
Removable combustor and inspection holes on gas turbine makes on-site inspection easier.
5

M5A-01

6

M1A Series Gas Turbine Generator Specifications
Site Condition for Normal Performance
Elevation above sea level:0m
Inlet Air Temperature: 15 °C
Inlet Air Pressure Loss
: 0.98 kPa
Exhaust Gas Pressure Loss
: 2.45 kPa
LHV of Natural Gas Fuel: 35.9 MJ/Nm3(100% CH4)				
Typical Steam Condition
Steam Pressure: 0.83 MPaG
Steam Temperature (Saturated) : 177 °C		Feed Water Temperature: 80 °C		
Blowdown from HRSG
: 0 %		

M1A Series

M1A Gas Turbine Series

M1A Gas Turbine Series
M1A-17

M1A-17D

GPB17

kJ/kWe-hr

1,450

1,090

730

1,450

1,090

730

2,850

2,140

1,430

2,850

2,140

1,430

1,755

1,315

875

1,755

1,315

875

15,13016,50019,75015,28016,66019,90015,35016,80020,19015,51016,96020,37017,32013,12014,37017,320

441

368

534

448

374

523

441

370

534

13,12014,370

524

449

375

526

443

377

526

443

377

28.8

29.2

29.6

28.5

29.0

29.4

57.6

58.5

59.2

57.0

58.0

58.8

28.8

29.4

29.9

28.8

29.4

29.9

5.0

79.2

kJ/kWe-hr

3.8

2.8

5.1

3.9

2.8

9.9

7.6

5.6

10.2

7.8

5.7

5.0

3.9

2.9

5.0

3.9

2.9

73.6

65.4

79.7

74.2

66.1

78.8

73.3

65.2

79.3

73.9

65.9

80.4

75.4

67.5

80.4

75.4

67.5

1,620

1,450

1,120

1,630

1,450

1,116

2,945

2,850

2,210

2,950

2,850

2,190

2,050

1,755

1,305

2,050

1,755

1,305

14,69015,13016,88014,81015,28017,14015,15015,35017,20915,29015,51017,475

12,46013,12014,93012,46013,12014,930

516

524

547

526

534

559

485

523

547

492

534

559

511

526

560

511

526

560

30.9

28.8

25.2

30.7

28.5

24.8

62.1

57.6

50.3

61.7

57.0

49.7

31.5

28.8

24.4

31.5

28.8

24.4

5.2

5.0

4.8

5.3

5.1

4.9

9.4

9.9

9.5

9.6

10.2

9.7

5.2

5.0

4.7

5.2

5.0

4.7

76.5

79.2

82.4

77.8

79.7

82.8

73.4

78.8

82.1

75.7

79.3

82.5

78.6

80.4

83.0

78.6

80.4

83.0

M1A/T-13 Series
Standard Package Configuration
M1A-13A Gas Turbine- Industrial Single-Shaft- Rotor Speed : 22,000 rpm
M1T-13A Gas Turbine- Twin M1A GT with Combined Gear Box
Compressor- 2 Stage Centrifugal- Pressure Ratio 9.4:1 (-13A), 9.6:1 (-13D)- Inlet Guide Vane (IGV) (-13D Option)
Combustor- Single Can Combustor- Single Ignition- Conventional Diffusion (-13A)- Water/Steam Injection to Diffusion Combustor(-13A Option)- Dry Low Emission (DLE) (-13D)- Applicable Fuel : Natural Gas, Diesel, Dual Fuel(-13A)
Turbine- 3 Stage Axial Turbine
Coupling Shaft & Cover- Flexible Coupling with Shear Pin and Cover			

GPB17D

Enclosed Package
Reduction Gear Box- Carbon Steel Common Base Frame- Epicyclic (M1A), Parallel (M1T)- Output Speed : 1,500 / 1,800 rpm (50/60 Hz)		 - Outdoor Carbon Steel, Acoustic Enclosure- Noise Level : 85 dBA at 1 m to the side of Enclosure
Starting and Turning Motor System- Forced Ventilation Fan with Filter and Inlet Screen- Variable Frequency Drive (VFD)(M1A)- Maintenance Stage, Ladder, Beam
- Air Starter, DC Motor(M1T)/(M1A Option)
Intake Silencer & Filter- Turning Motor- Painted Carbon Steel (Outer Skin and Structure)
Lube Oil System- Stainless Steel Inner Punching Metal Sheet- Lube Oil : Synthetic Ester Oil- 2 Stage Filter- Gearbox Driven Main Lube Pump
- Pulse Type Self Cleaning Filter (Option)- DC Motor Driven Pre-Post Lube Pump
- Noise Level : 85 dBA at 1m from Filter inlet- Air Cooled Oil Cooler with Temp. Control Valve
Controls					- Water Cooled Oil Cooler(Option)- Programmable Logic Controller (PLC)- Integral Oil Reservoir : 210 liter (M1A-13A)(CPU, Power Module : Redundant): 160 liter (M1T-13A)- Gas Turbine and Generator Control- Simplex Filter (Option: Duplex Type)GT start / shutdown Control			- Oil Mist Separator
Speed / kW / Power Factor Control
Generator
Auto Synchronizing and Load Sharing			- Continuous Duty Rating- Touch Panel Operation- Air Cooled Open Drip-Proof Construction- Ethernet or Serial Communication to DCS/SCADA		
- 3 Phase, 3 Wire (Option : 4 Wire)- Remote Monitoring (Option)- Standard Voltage : 3.3 kV, 6.6 kVGraphics Monitoring- Power Factor : 90% (Option : 85%, 80%)Lag
Historical Trend & Event Logger- Bearing : Ball (Roller) Bearing
Daily and Monthly Reports			
- Lubrication : Grease Pack		
- Exciter : Brushless		

M1A-17 Series
Standard Package Configuration

Starting and Turning Motor System- Variable Frequency Drive (VFD)- (Option : Air Starter, DC Motor)- Turning Motor			

M1A-17 Gas Turbine- Industrial Single-Shaft- Rotor Speed : 22,000 rpm
Compressor- 2 Stage Centrifugal- Pressure Ratio 10.5:1 (-17,-17D)- Inlet Guide Vane (IGV) (-17D Option)
Combustor- Single Can Combustor- Single Ignition- Conventional Diffusion (-17)- Dry Low Emission (DLE) (-17D)- Applicable Fuel : Natural Gas, Diesel, Dual fuelTurbine- 3 Stage Axial Turbine

Lube Oil System- Lube Oil : Synthetic Ester Oil- Gearbox Driven Main Lube Pump
- DC Motor Driven Pre-Post Lube Pump
- Air Cooled Oil Cooler with Temp. Control Valve- Water Cooled Oil Cooler(Option)- Integral Oil Reservoir : 240 liter- Simplex Filter (Option : Duplex Type)- Oil Mist Separator

Enclosed Package- Carbon Steel Common Base Frame		- Outdoor Carbon Steel, Acoustic Enclosure- Noise Level : 85 dBA at 1 m to the side of Enclosure- Forced Ventilation Fan with Filter and Inlet Screen- Maintenance Stage, Ladder, BeamIntake Silencer & Filter- Painted Carbon Steel (Outer Skin and Structure)- Stainless Steel Inner Punching Metal Sheet- 2 Stage Filter- Pulse Type Self Cleaning Filter (Option)- Noise Level : 85 dBA at 1m from Filter inlet

P8 200818

Coupling Shaft & Cover- Flexible Coupling with Shear Pin and Cover

Generator- Continuous Duty Rating- Air Cooled Open Drip-Proof Construction- 3 Phase, 3 Wire (Option 4 Wire)- Standard Voltage : 3.3 kV, 6.6 kV- Power Factor : 90% (Option : 85%, 80%)Lag- Bearing : Ball (Roller) Bearing- Lubrication : Grease Pack
- Exciter : Brushless				

Reduction Gear Box- Epicyclic- Output Speed : 1,500 / 1,800 rpm (50/60 Hz)		
				

GPB17/17D Typical Package Outlook : m

Controls					- Programmable Logic Controller (PLC)(CPU, Power Module : Redundant)- Gas Turbine and Generator Control
GT start / shutdown Control			
Speed / kW / Power Factor Control
Auto Synchronizing and Load Sharing			- Touch Panel Operation- Ethernet or Serial Communication to DCS/SCADA		- Remote Monitoring (Option)
Graphics Monitoring
Historical Trend & Event Logger
Daily and Monthly Reports

GPB17/17D Typical Layout : m(Reference)(Reference)

Ventilation Exhaust

21.5
AIR COMPRESSOR & TANKHRSG FEED WATER TANKGAS COMPRESSORCONTROL ROOM

5.5

GAS VALVE UNIT

FEED WATER PUMP

HRSG

11.0

TurbineAir Intake

2.4

Ventilation
Air Intake
GAS TURBINE GENERATOR SET
6.0

7

8

M5A Series Gas Turbine Generator Specifications

M7A Series Gas Turbine Generator Specifications

Site Condition for Normal Performance
Elevation above sea level:0m
Inlet Air Temperature: 15 °C
Inlet Air Pressure Loss
: 0.98 kPa
Exhaust Gas Pressure Loss
: 2.94 kPa
LHV of Natural Gas Fuel: 35.9 MJ/Nm3(100% CH4)				

Site Condition for Normal Performance
Elevation above sea level:0m
Inlet Air Temperature: 15 °C
Inlet Air Pressure Loss
: 0.98 kPa
Exhaust Gas Pressure Loss
: 2.94 kPa		
LHV of Natural Gas Fuel: 35.9 MJ/Nm3(100% CH4)

Typical Steam Condition
Steam Pressure: 0.83 MPaG
Steam Temperature (Saturated) : 177 °C
Feed Water Temperature: 80 °C		
Blowdown from HRSG
: 0 %			Typical Steam Condition
Steam Pressure
Steam Temperature (Saturated)
Feed Water Temperature
Blowdown from HRSG

M5 Series: 0.83 MPaG
: 177 °C		: 80 °C		: 0 %			M7A Gas Turbine Series

M5A Gas Turbine Series
M5A-01D
GPB50D

3,535

11,10012,120

516

523

62.6

52.6

10.6

9.2

81.8

82.1

0

M5A Series
Standard Package Configuration

Compressor- 11 Stage Axial Flow
- Pressue Ratio 15.5:1- Inlet Guide Vane (IGV) & 3 Stage Variable
Stator Vane (VSV)
Combustor- 6 Can Combustors- Dual Ignition System- Dry Low Emission (DLE)- Applicable Fuel : Natural Gas
Turbine- 3 Stage Axial Turbine
Coupling Shaft & Cover- Flexible Coupling with Shear Pin and CoverReduction Gear Box- Epicyclic- Output Speed : 1,500/1,800rpm (50/60Hz)

16,080
526
51.5
9.1
81.0

15

3,830

10,830

11,63013,58010,83011,780

14,230

525

448

379

525

516

563

97.3

97.0

96.8

97.3

84.3

66.4

17.0

13.1

9.7

17.0

14.4

13.1

83.1

78.8

71.9

83.1

82.6

83.8

3,720

8,220

7,660

6,040

8,220

7,660

6,040

10,69010,83011,78010,69010,83011,780

506

516

544

519

525

554

519

525

554

66.5

62.6

54.8

101.1

97.3

84.0

101.1

97.3

84.0

10.8

10.6

10.3

17.2

17.0

16.3

17.2

17.0

16.3

79.9

81.8

85.0

81.5

83.1

86.3

81.5

83.1

86.3

Intake Silencer & Filter- Painted Carbon Steel (Outer Skin and Structure)- Stainless Steel Inner Punching Metal Sheet- 3 Stage Filter- Pulse Type Self Cleaning Filter (Option)- Noise Level : 85 dBA at 1 m from Filter inlet

Lube Oil System- Lube Oil : Turbine Oil ISO VG32/46- Turbine Driven Main Lube Oil Pump
- AC Motor Driven Pre-Post Lube Pump
- DC Motor Driven Emergency Post Lube Pump
Controls- Air/Water Cooled Oil Cooler with Temp. Control Valve - Programmable Logic Controller (PLC)- Integral Oil Reservoir : 1,500 liter(CPU, Power Module : Redundant)- Oil Heater (Option : Cold Weather )- Gas Turbine and Generator Control- Simplex Filter (Option : Duplex Filter)
GT start / Shutdown Control- Oil Vapor Fan
Speed / kW / Power Factor Control
Auto Synchronizing and Load Sharing
Generator- Touch Panel Operation- Continuous Duty Rating- Ethernet or Serial Communication to DCS/SCADA- 3 Phase, 3 Wire (Option : 4 Wire)- Remote Monitoring (Option)- Standard Voltage : 6.6 kV, 11.0 kVGraphics Monitoring- Power Factor : 90% (Option : 85%,80%) Lag
Historical Trend & Event Logger- Bearing : Sleeve Bearing
Daily and Monthly Reports- Lubrication : Forced Oil Lubrication- Exciter : Brushless

M7A Series
Standard Package Configuration
M7A-03 Gas Turbine- Industrial Single-Shaft- Rotor Speed : 13,790 rpm

Combustor- 6 Can Combustors- Dual Ignition System- Conventional Diffusion (-03)(Option De-NOx : Steam Injection Type)- Dry Low Emission (DLE) (-03D)- Applicable Fuel : Natural Gas, Diesel＊Notes : Diesel is only for standby use

GPB80/80D Typical Package Outlook : m

Ventilation
ExhaustCONTROL ROOMGAS COMPRESSOR

TurbineAir Intake

GAS COMPRESSORGAS VALVE UNIT

COOLING TOWER
FEED WATERCOOLING WATER PUMP
PUMP

Ventilation
Air Intake

TurbineExhaustGAS TURBINE GENERATOR SET

HRSG FEED WATER TANK

3.4

3.5

FEED WATERCOOLING WATER PUMP
PUMP

Controls- Programmable Logic Controller (PLC)(CPU, Power Module Redundant)- Gas Turbine and Generator Control
GT start / shutdown Control
Speed / kW / Power Factor Control
Auto Synchronizing and Load Sharing- Touch Panel Operation- Ethernet or Serial Communication to DCS/SCADA- Remote Monitoring (Option)
Graphics Monitoring
Historical Trend & Event Logger
Daily and Monthly Reports

AIR COMPRESSOR & TANKHRSG FEED WATER TANKGAS VALVE UNIT

Intake Silencer & Filter- Painted Carbon Steel (Outer Skin and Structure)- Stainless Steel Inner Punching Metal Sheet- 3 Stage Filter- Pulse Type Self Cleaning Filter (Option)- Noise Level : 85 dBA at 1m from Filter Inlet

26.0

3.3

13.5

CONTROL ROOM

Enclosed Package- Carbon Steel Common Base Frame- Painted Carbon Steel Acoustic Enclosure- Noise Level : 85 dBA at 1 m to the side of
Enclosure- Forced Ventilation Fan with Filter andInlet Screen- Maintenance Stage, Ladder, Beam

GPB80/80D Typical Layout : m(Reference)

4.0
COOLING TOWER

Ventilation
Air Intake

Generator- Continuous Duty Rating- 3 Phase, 3 Wire (Option : 4 Wire)- Standard Voltage : 6.6 kV, 11.0 kV- Power Factor : 80% Lag- Bearing : Sleeve Bearing- Lubrication : Forced Oil Lubrication- Exciter :Brushless(Reference)
AIR COMPRESSOR & TANK

TurbineAir Intake

Lube Oil System- Lube Oil : Turbine Oil ISO VG32/46- Turbine Driven Main Lube Oil Pump
- AC Motor Driven Pre-Post Lube Pump
- DC Motor Driven Emergency Post Lube Pump
- Air/Water Cooled Oil Cooler with Temp. Control Valve- Integral Oil Reservoir : 2,750 liter- Oil Heater (Option : Cold Weather )- Simplex Filter (Option : Duplex Filter)- Oil Vapor Fan

P10
GPB80D

Coupling Shaft & Cover- Flexible Coupling with Shear Pin and Cover- Carbon Steel Common Base Frame- Painted Carbon Steel Acoustic Enclosure- Noise Level : 85 dBA at 1 m to the side of Enclosure- Forced Ventilation Fan with Filter and Inlet Screen- Maintenance Stage, Ladder, Beam

Reduction Gear Box- Epicyclic- Output Speed : 1,500 / 1,800 rpm (50/60 Hz)
Starting and Turning System- Variable Frequency Drive (VFD)

Compressor- 11 Stage Axial Flow
- Inlet Guide Vane (IGV) & 3 Stage Variable
Stator Vane (VSV)- Pressure Ratio 16:1

Turbine- 4 Stage Axial Turbine

Enclosed Package(Reference)

6.5

5,740

12,180

23.5

9

7,660

11,100GPB50D Typical Layout : m

8.7

3,830

10,890(Reference)

TurbineExhaust

5,740

4,715

GPB50D Typical Package Outlook : m

Ventilation
Exhaust

7,660

5,165

Starting and Turning System- Variable Frequency Drive (VFD)

M5A-01 Gas Turbine- Industrial Single-Shaft- Rotor Speed : 18,000 rpm

2,355

15.0

4,715

HRSG

11.0

1.4

GAS TURBINE GENERATOR SET

HRSG

10

L20A Series Gas Turbine Generator Specifications

L30A Series Gas Turbine Generator Specifications

Site Condition for Normal Performance
Elevation above sea level:0m
Inlet Air Temperature: 15 °C
Inlet Air Pressure Loss
: 0.98 kPa
Exhaust Gas Pressure Loss
: 3.43 kPa
LHV of Natural Gas Fuel: 35.9 MJ/Nm3(100% CH4)				

Site Condition for Normal Performance
Elevation above sea level:0m
Inlet Air Temperature: 15 °C
Inlet Air Pressure Loss
: 0.98 kPa
Exhaust Gas Pressure Loss
: 3.43 kPa
LHV of Natural Gas Fuel: 35.9 MJ/Nm3(100% CH4)

Typical Steam Condition
Steam Pressure: 0.83 MPaG
Steam Temperature (Saturated) : 177 °C
Feed Water Temperature: 80 °C		
Blowdown from HRSG
: 0 %			Typical Steam Condition
Steam Pressure
Steam Temperature (Saturated)
Feed Water Temperature
Blowdown from HRSG

M7A/L20A Series: 0.83 MPaG
: 177 °C
: 80 °C		
:0%

L20A Gas Turbine Series

L30A Gas Turbine Series

L20A-01/01D

L30A-01/01D
GPB300 / 300D

11,510

545

517

213

188

39.7

32.5

84.0

82.4

0

15

24.5
77.7

9,660

11,770

519

481

506

315.8

284.2

245.2

54.1

43.4

40.8

84.3

82.4

82.8

0

15

34,12032,36024,66010,50010,69011,380

8,890

9,110

9,910

538

545

565

487

519

548

221

213

193

334.3

315.8

267.3

40.2

39.7

38.8

51.1

54.1

51.0

82.5

84.0

86.7

81.6

84.3

87.3

Starting and Turning System- Variable Frequency Drive (VFD)- Forced Ventilation Fan with Filter and Inlet Screen- Maintenance Stage, Ladder, Beam

Lube Oil System

Intake Silencer & Filter- Painted Carbon Steel (Outer Skin and Structure)- Stainless Steel Inner Punching Metal Sheet- 3 Stage Filter- Pulse Type Self Cleaning Filter (Option)- Noise Level : 85 dBA at 1 m from Filter inlet

Coupling Shaft & Cover- Flexible Coupling with Shear Pin and CoverControls- Programmable Logic Controller (PLC)(CPU, Power Module : Redundant)- Gas Turbine and Generator Control
GT start / Shutdown Control
Speed / kW / Power Factor Control
Auto Synchronizing and Load Sharing- Touch Panel Operation- Ethernet or Serial Communication to DCS/SCADA- Remote Monitoring (Option)
Graphics Monitoring
Historical Trend & Event Logger
Daily and Monthly Reports

GPB180
Enclosed Package

GPB180/180D Typical Layout : m

GPB180/180D Typical Package Outlook : m

L30A-01 Gas Turbine- Industrial Twin-Shaft- Power Turbine Rotor Speed : 5,600 rpm

Lube Oil System- Lube Oil : Turbine Oil ISO VG32 (optional VG46)- Motor Driven Lube Oil Pump
- Water Cooled Oil Cooler with Temp. Control Valve- Integral Oil Reservoir : 11,700 liter- Duplex Filter- Oil Vapor Fan

Controls- Programmable Logic Controller (PLC)(CPU, Power Module : Redundant)- Gas Turbine and Generator Control
GT start / Shutdown Control
Speed / kW / Power Factor Control
Auto Synchronizing and Load Sharing- Touch Panel Operation- Ethernet or Serial Communication to DCS/SCADA- Remote Monitoring (Option)
Graphics Monitoring
Historical Trend & Event Logger
Daily and Monthly Reports

Generator- Continuous Duty Rating- Water Cooled (Option : Air-to-Air Cooled)- 3 Phase, 3 Wire (Option : 4 Wire)- Standard Voltage : 11.0 kV- Power Factor : 90% (Option : 85%, 80%) Lag- Bearing : Sleeve Bearing- Lubrication : Forced Oil Lubrication- Exciter : Brushless

GPB300

Enclosed Package- Carbon Steel Common Base Frame- Painted Carbon Steel Acoustic Enclosure- Noise Level : 85 dBA at 1 m to the side of Enclosure

Ventilation
Air Inlet

GPB300/300D Typical Layout : m
40.0(Reference)

TurbineAir Intake

AIR COMPRESSOR & TANKELECTRICAL ROOMCONTROL ROOM

50.0

10.7
4.9

ExhaustGas Outlet

CONTROL ROOM
TRANSFORMERAIR COMPRESSOR & TANKYARDHRSG FEED WATER
TANK

Ventilation
Exhaust25.0

GAS COMPRESSORCOOLING
WATER
PUMP
FEED
WATER
PUMP
HRSG FEED WATERGAS VALVE UNIT
TANK

10.2

Intake Silencer & Filter- Painted Carbon Steel (Outer Skin and Structure)- Stainless Steel Inner Punching Metal Sheet- 3 Stage Filter- Pulse Type Self Cleaning Filter (Option)- Noise Level : 85 dBA at 1 m from Filter inlet

P12 200818

Combustor- 8 Can Combustors- Dual Ignition System- Conventional Diffusion (-01)(Option De-NOx : Steam Injection)- Dry Low Emission (DLE) (-01D)- Applicable Fuel : Natural Gas, Diesel*Notes : Diesel is only for standby use
Turbine- Gas Generator Turbine : 2 Stage Axial Turbine- Power Turbine : 3 Stage Axial Turbine

42.0

Ventilation Exhaust- Forced Ventilation Fan with Filter and Inlet Screen- Maintenance Stage, Ladder, Beam

Starting and Turning System- Variable Frequency Drive (VFD)

Compressor- 14 Stage Axial Flow
- Pressure Ratio 24.9:1- Inlet Guide Vane (IGV) & 4 Stage Variable
Stator Vane (VSV)(Reference)

COOLING TOWER

TurbineAir Intake

Reduction Gear Box- Parallel- Output Speed : 1,500/1,800rpm (50/60Hz)

GPB300/300D Typical Package Outlook : m(Reference)(Reference)

L30A Series
Standard Package Configuration

Coupling Shaft & Cover- Flexible Coupling with Shear Pin and Cover- Carbon Steel Common Base Frame- Painted Carbon Steel Acoustic Enclosure- Noise Level : 85 dBA at 1 m to the side of Enclosure

Ventilation
Air Inlet

16,18015,080Generator- Continuous Duty Rating- Water Cooled- 3 Phase, 3 Wire (Option : 4 Wire)- Standard Voltage : 6.6 kV, 11.0 kV- Power Factor : 85%Lag- Bearing : Sleeve Bearing- Lubrication : Forced Oil Lubrication- Exciter : Brushless

Reduction Gear Box- Parallel- Output Speed : 3,000/3,600rpm (50/60Hz)

182

24,2709,110

17,970Combustor

GPB180 P11- 8 Can Combustors- Dual Ignition System- Dry Low Emission (DLE) (-01D)- Applicable Fuel : Natural Gas, Diesel*Notes : Diesel is only for standby use
Turbine- 3 Stage Axial Turbine

443

32,36019,320- Lube Oil : Turbine Oil ISO VG32
- Turbine Driven Main Lube Oil Pump
- AC Motor Driven Pre-Post Lube Pump
- DC Motor Driven Emergency Post Lube Pump
- Water Cooled Oil Cooler with Temp. Control Valve- Integral Oil Reservoir : 5,900 liter- Oil Heater- Duplex Filter- Oil Vapor Fan

Compressor- 11 Stage Axial Flow
- Pressure Ratio 18.6:1- Inlet Guide Vane (IGV) & 4 Stage Variable
Stator Vane (VSV)

8,980
13,200HRSG FEED WATER HRSG
PUMPGAS VALVE UNIT
COOLING
WATER
PUMP

HRSG
GAS TURBINE GENERATOR SET

11

COOLING TOWER

24.3
0.5

17.4

12.0

L20A-01 Gas Turbine- Industrial Single-Shaft- Rotor Speed : 9,420 rpm

13,47010,690GAS TURBINE GENERATOR SET

L20A Series
Standard Package Configuration

17,970GAS COMPRESSOR

12

Kawasaki Techno-Net

Installation Examples
Kawasaki Gas Turbine has been installed to....

Full Time Support
Maintenance Management● Data Center

Predictive services based on trending data and asset maintenance management

What to do

When to do it

How to do it

Who's to do it

Improvement of Availability and Quality of Maintenance
Minimum down time and good quality with adequate maintenance strategies and execution.

Remote Maintenance System by a GT Expert
Proven effectiveness by most Kawasaki remote maintenance users
Fleet wide analysis● Paper Mill● Food Process● College Campus● Tire Manufacturer● District Heat & Cooling● Hospital● Oil & Gas

AND MORE !!!

In 2010 Kawasaki accumulated 10,000th Kawasaki Gas Turbine Engines
in all over the world !!!
M1 Series

Techno-Net system continuously monitors
the Gas Turbine Plant in any region of the world
Three main features of Techno-Net system
Global remote monitoring

Preventing serious failures

Maintenance management

Remote monitoring through the internet

Enforced monitoring and diagnosis

Adequate management of maintenance

GPB15D USA

GPS4000 USA

GPB30 SOUTH KOREA

M7 Series

Connection of centers through the internet

GPB80D ITALY

GPB80D MALAYSIA

GPB80D FRANCEGPB80D ITALY

M5 Series Coming Soon!

L20 Series

GPB180 PORTUGALCommunications through the telephone net / internet
between customer and the centers

GPB180D MALAYSIA

L30 Series

Internet / Intranet

The Kawasaki World Business Center in the USA, Germany, Malaysia, China, Korea and Japan are connectedby the Internet and by the KHI intranet to monitor gas turbines remotely and globally.

Attended monitoring
All system data is monitored and recorded hourly, as well as all start signals and first out malfunction signals.
Predictive and preventative maintenance is accomplished by analysis of thermal cycles and unit vibration.

13

GPB180 JAPANGPB300 JAPAN

14