A L P H A ’ S N E X T- G E N E R A T I O N U N I N T E R R U P T I B L E P O W E R S U P P LY

next-generation power
From ground-breaking transformer design to the most intuitive and user-friendly interface in theindustry, the XM3-HP sets the new standard in intelligent power management.

The Alpha XM3-HP CableUPS incorporates significant technological advancements across the entire power technology
platform. These advancements focus on delivering three primary benefits: improved efficiency, optimized performance andreduced operating costs. The XM3-HP also incorporates a wide-range features including:AlphaGuard™

Alpha Smart-Display

Embedded battery balancing to maximize battery life andoptimize performance

Four-line display with intelligent, virtual keypad for optimal provisioning
and diagnostics

Advanced Ferro Technology

Advanced Battery Management

Maximum power efficiency under all modes of operation

Dynamic 5-stage charger technology maximizes AlphaCell® battery life

AlphaApps

AlphaNet™ DOCSIS®-Based Communications

Intelligent diagnostics for remote preventative maintenance of batteries
and power train

Intelligent monitoring and power system management

Alpha DOC
Dual Output Controller (DOC) provides two programmable outputs from asingle XM3-HP

Advanced Efficiency Technology
The Alpha XM3-HP triple efficiency ferro technology optimizes the power supply’s performance,
resulting in significantly reduced utility power consumption and a direct savings in network operations.

h Exclusive Patent Protected Design
Moving the inverter winding to the output side of the ferro transformer
minimizes conversion losses, improving overall inverter efficiency.

h Highest Line Mode Efficiency
The XM3-HP offers the highest line mode efficiency available,
requiring less AC utility power to support a load.

h Tightest Output Voltage Regulation
Alpha’s XM3-HP provides the tightest output voltage regulation everoffered to reduce I2R cable power losses.

h Maximum Inverter Efficiency
Significant gains in inverter efficiency directly translates into increased
battery runtimes, further improving network performance and power
outage recovery capabilities.

h Load Optimization

Guide for Optimal Efficiency

The XM3-HP is available in several models tobest match network load requirements.

Maximum Efficiency

XM3-918E-HP
XM3-910HP

XM3-615CE-HP
XM3-615M-HP XM3-915E-HP
XM3-915P-HP XM3-915-HP

XM3-622CE-HP
0A

2A

4A

6A

8A

10A

12A

14A 90V

0A

3A

6A

9A

12A

15A

18A

21A 60Vadvanced battery management
The Alpha XM3-HP’s advanced battery management optimizes battery life and contributes toreducing both capital expenditures and on-going operating costs.

h Embedded Battery Balancing
The Alpha XM3-HP embedded AlphaGuard uses advanced battery balancing technology to redirect current from overcharged batteries to the undercharged battery,
optimizing battery service life.
AlphaGuard—Balancing
2500mA

AlphaGuard—Balanced

1300mA

12.66VDC

1200mA

14.00VDC

13.87VDC

13.62VDC

13.62VDC

Battery Charger Float Voltage: 40.86VDC

h Extended Runtime
The Alpha XM3-HP’s advanced battery management and increased
inverter efficiency maximizes battery runtime in the network.
AlphaCell HP (Estimated runtime minutes using XM3-HP @ 90VAC)
4A
6A
8A

10A

3.5HP

4.0HP

3.5HP

4.0HP

3.5HP

4.0HP

3.5HP

4.0HP

540

588

358

394

263

295

204

234

1144

1264

771

841574

624

450

491

12A

14A

16A

3.5HP

4.0HP

3.5HP

4.0HP

3.5HP

4.0HP

165

193

137

164

116

142

368

404

308

342

264

295

AlphaCell GXL (Estimated runtime minutes using XM3-HP @ 90VAC)
4A
6A
8A

10A

195GXL

220GXL

195GXL

220GXL

195GXL

220GXL

195GXL

220GXL

476

550

313

363

229

265

177

205

1026

1177

685

789

506

585

396

458

12A
Models:3 Batteries:
6 Batteries:

13.62VDC

Battery Charger Float Voltage: 40.86VDC

B U L K | A C C E P T | F L OAT | R E F R E S H | R E S T

Models:3 Batteries:
6 Batteries:

300mA

Optimal float voltage is 13.62VDC @ 25°C/77°F

The Alpha XM3-HP’s dynamic 5-stage battery charging technology
provides system batteries with optimal charge management.

Models:3 Batteries:
6 Batteries:

300mA

Batteries are balanced within ±0.1VDC
Float voltage across each battery is equal (13.62VDC @ 25°C/77°F)

h Dynamic Multi-Stage Charging

Models:3 Batteries:
6 Batteries:

300mA

14A

16A

195GXL

220GXL

195GXL

220GXL

195GXL

220GXL

142

164

118

136

99

115

322

373

269

311

229

266

advanced intelligence platform
The Alpha XM3-HP’s internal intelligence provides Network Operation Centers (NOC) with the critical andhighly relevant data necessary to reduce operating expenses through remote management.

h Integrated DOCSIS® Communications

h Integrated AlphaApps

The XM3-HP can be used as a network test probe when equipped with an
AlphaNet DM3.0 integrated management hub, integrated DOCSIS enables
access to all of the XM3-HP’s advanced information and diagnostics:

Power reliability algorithms use real-time data to predict service intervals,
battery replacements and offer real-time insights into the health of your
HFC network via standard EMS interface. Parameters include:• Full Spectrum Capture• Battery Health• Utility Performance Reports• Bonded Channel Micro Reflections• Remaining Battery Runtime• Utility Meter• Bonded Channel Constellations• Trending Battery MHOs

AlphaNet™ DOCSIS Status Monitor
Spectrum

Live
Full Range

Average

Last

SavedFrequency

Full Range
Restart

57.02

Stop

Center Frequency

502.3 MHz

Span

1005 MHz

Start Frequency

0 MHz

Stop Frequency

1005 MHz

Resolution Bandwidth

1 MHz

Amplitude
Maximum

30dBmV

Minimum

70dBmV

Measurements
Peak6.67 dBmV

Peak Position

751.41 MHz

Marker 1

MHzPower
Marker 2

MHz

PowerFrequency
Max Hold

Save 1

Save 2

PowerClear

DOCSIS Communications Menus
COMM – GENERAL
CM MAC ADDRESSCOMM – GENERALCM IP ADDRESS

192.168.1.120

00:90:EA:00:36:EAhi

MAC Address

ESC

hi

IP AddressESCXM3-HP CableUPS® International Specifications
Models:

11/2015915M-HP

915P-HP

910E-HP

915E-HP

615CE-HP

622CE-HP

908HP

910HP

915HP

918HP

Nominal AC Input Voltage (VAC):

127

200-240200-240200-240

230

230

120

120

120

120

Nominal Input Frequency:

60Hz

60Hz

50Hz

50Hz

50Hz50Hz60Hz60Hz

60Hz60Hz

Input Frequency Tolerance (%):

±3±3±3±3±3±3±3±3±3±3

Input Voltage Operating Range Tolerance (%):

-34 / +15-30 / +20-30 / +20-30 / +20-30 / +20-30 / +20-30 / +15-30 / +15-30 / +15-30 / +15

Output Voltage (VAC):

63 / 89

63 / 89

48 / 63 / 89

63 / 89

48 / 6363

63 / 89

63 / 89

63 / 89

63 / 89

Parameters

Output Voltage Regulation:-5 / +1-5 / +1-5 / +1-5 / +1-6 / +1.5-6 / +1.5-5 / +1-5 / +1-5 / +1-5 / +1

Maximum Rated Output Current:

15 Amps

15 Amps

15 / 10 Amps

22 / 15 Amps

15 Amps

22 Amps

8 Amps

10 Amps

15 Amps

18 Amps

Output Power (VA):

1350

1350

900

1350

900

1408

720

900

1350

1620

Line Mode Efficiency:

Up to 94%

Standby Efficiency:

Up to 91%

Bulk Charger Current (@ 80% Load & Nom Line):
Battery Voltage (VDC):*XM2-622CE will continue as a 48V model until further notice.

10 Amps

10 Amps

10 Amps

10 Amps

10 Amps

10 Amps

10 Amps

10 Amps

10 Amps

10 Amps

36363636

36

36*36

36363660 / 27.2

60.5 / 27.5

Mechanical
Inverter Module:

Front plug in, hot-swappable inverter module

Dimensions H x W x D (in/mm):

7.8 x 15 x 10 / 198.1 x 381 x 254, With Handle: 7.8 x 16.7 x 10.7 / 198.1 x 424.18 x 271.8

Weight (lb/kg):

60 / 27.2

60 / 27.2

53 / 24.1

67 / 30.5

53 / 24.1

Input Power Connector:

67 / 30.5

48.5 / 22.0

49 / 22.3

IEC 320 / C20

Battery Connector:

Anderson style 75 Amps

Remote Temperature Sensor:

Ring lug fastens to negative terminal on center battery

Display:

4 line x 20 character blue LCD screen with soft-key menu controls

LRI Connector:

Anderson PP30’sMounting:

Shelf mounts inside suitably rated electrical enclosure

Environment
Operating Temperature:-40 to 60°C / -40 to 140°F (derate by 2°C / 3.6°F per 1,000 feet above 3,000 feet)

Storage Temperature:-40 to 70°C / -40 to 158°F

Humidity:

0 to 95% non-condensing (relative)

Conformal Coating:

All printed circuit board assemblies to prevent moisture related failure

Voltage
Name Plate Rating (VAC):

127

200-240200-240200-240230

230

110-127

110+127110-127110-127

Input Window (% of Nominal Input):-34 / +15-30 / +20-30 / +20-30 / +20-30 / +20-30 / +20-30 / +15-30 / +15-30 / +15-30 / +15

Input Range (VAC):

84-146161-276

161-276

161-276

161-276

161-276

84-13884-13884-13884-138Output Voltage Regulation (%):

-5 / +1-5 / +1-5 / +1-5 / +1-6 / +1.5-6 / +1.5-5 / +1-5 / +1-5 / +1-5 / +1

Load Range:

1-15 Amps

1-15 Amps

1-10 Amps

1-15 Amps

1-15 Amps

1-22 Amps

1-8 Amps

1-10 Amps

1-15 Amps

1-8 Amps

Output Voltage Min/Max (VAC):

84.6 / 90

84.6 / 90

84.6 / 90

84.6 / 90

59.2 / 64

59.2 / 64

84.6 / 90

84.6 / 90

84.6 / 90

84.6 / 90

UL/CSA 60950-1, UL 1778, CSA 107.3 (NRTL/C):

ü

ü

ü

ü

ü

ü

IEC 60950-1 (CB):

üü

ü

ü

ü

ü

ü

üü

ü

ü

ü

NRTL/C

NRTL/CCE

CE

NRTL/C

NRTL/C

NRTL/C

NRTL/C

üü

ü

ü

ü

ü

Safety Compliance

IEC 62040-1:
Safety Mark:EMC Compliance
FCC Part 15 Class A:
IEC/EN 50083-2 (CATV):üü

IEC/EN 65040-2 (UPS):

üü

ü

ü

CISPR22 Class A:üüüüWorldwide Corporate Offices
North America

EuropeLatin America

Asia PacificTel: +1 360.647.2360
Fax: +1 360.671.4936

Tel: +49 9122.79889.0
Fax: +49 9122.79889.21

Tel: +561 792.9651
Fax: +561 792.7157

Tel: +852 2736.8663
Fax: +852 2199.7988