CXPS-HX
2500A-5000A Power System• -48V Distributed power solution for CO’s, MSC’s,
Data Center and Cable Headend facilities (DPCO)• Each 2500A bay combines rectifiers, battery
termination and distribution• Dual bay kit links two 2500A bays doubling capacity,breakers and termination• High efficiency modular rectifiers reduce operating costs• Flexible low voltage load disconnect, circuit breaker,
TPS and TPL fuse options

The CXPS-HX System provides high capacity
DC power for large communication network
applications.
This system combines the capabilities of tiered distribution, advanced
microprocessor based supervision, and modular rectifiers in a single
integrated bay. Two bays can easily be linked together and share acentral controller to double the system capacity.
The Cordex® Distributed Power System is cost effective due to theinternal copper buswork, and is delivered ready to assemble withfactory tested components. No overhead bus work is required.
An optional external return bus is available. Cable access is fromthe top and load connections are terminated from the side or rearof the bay. Hot swappable Cordex® power modules and internalbusswork provides a safe work environment with easy installationand maintenance.

1

CXPS-HX 48-2500 48V High Capacity Distributed Power System
P/N: Refer online to ordering guide for P/N and configurations
Electrical

Environmental
Temperature:

0 to 40°C (32 to 104°F)

Rectifier Shelf AC Input:•Single Phase, 208 to 277VAC•Dual 3 Phase, 208VAC (w/o neutral)•Dual 3 Phase, 480VAC (with neutral)•Dual 3 Phase, 480VAC (w/o neutral)

Humidity:

0 to 95% RH non-condensing

Elevation:-500 to 2800m (-1640 to 9186ft)

Max. Output Power:

120kW One bay system
240kW Two bay system

Related Components

Max. Bus Capacity:

2500A One bay system
5000A Two bay system

Cordex HP 48-4kW Rectifier:See datasheet #0480003-00 for more detailed information.

Cordex HP 48-12kW Rectifier:See datasheet #047-0259-00 for more detailed information.

System Level Alarms/Controls:

Alarms/control parameters are user-programmable through built-in
digital supervisory unit. See Cordex datasheet for detailed informationon alarms and controls.

Indicators:•LCD with touch screen•System OK (green LED)
•System minor alarm (yellow LED)
•System major alarm (red LED)

Load Disconnect:

 Fuse/CB panel mounted option••TPL + bolt-in panel 2000A rated•Bullet breaker panel 600A rated

Distribution and Termination
System distribution section consists of up to 3 distribution tiers.
Fuses

TPL Fuses:•61-800A•4 fuse holders per panel•Max 3 fuse panels per bay

TPS/TLS Fuses:•Up to 125A
•18 fuse holders per panel•Max 6 fuse panels per bay

Breakers

Alarm

Bolt-in Breakers:

Plug-in Bullet Breakers:•1 pole up to 250A
•2 pole 275 to 400A
•3 pole 450 to 600A
•4 pole 650 to 800A
•5 pole 850 to 1000A•6 pole 1050 to 1200A•12 breaker poles per panel•Max 3 fuse panels per bay

Connections:

Mounting:

2" Auxiliary framing (customer supplied)•1 pole up to 125A
•2 pole 126 to 200A
•3 pole 201 to 300A
•18 breaker poles per panel•Max 6 panels per bay

Termination:

124 sets of 2 hole ½" dia. on 1¾" centers or 3⁄8" dia. on 1" centers

Unit Capacity:

5,000A per bar

Ultimate Capacity:

2 bar limit (10,000A)

Smart Peripheral Modules

Shunt Monitoring:

6 shunts per module (3 or 5 modules per bay)

Remote Hot Bar

Remote Return Bar

Output Termination

TPL Fuse:

2 hole, 3⁄8" dia. on 1" center & ½" dia. on 1¾" center

TLS/TPS/AM Breaker:

1 pole, 2 hole, ¼" dia. on 5⁄8" center
2 and 3 pole, 2 hole, 3⁄8" dia. on 1" center

Internal Ground Bar (optional):

2 hole, ¼" dia. on ⁄8” center, ⁄8" dia. on 1" center& ½" dia. on 1¾" center

Battery:2 hole, 6 sets 3⁄8" dia. on 1" center & ½" dia. on 1¾" center

50.34 to 2.5mm2 (14 to 22AWG)

3Mechanical
Mounting:

Standard 23" relay rack (flush rack mount) in box bay

Dimensions:

cm: 213H x 71W x 71Dinches: 84H x 28W x 28DMounting:2" Auxiliary framing (customer supplied)

Termination:

124 sets of 2 hole ½" dia. on 1¾" centers or 3⁄8" dia. on 1" centers

Unit Capacity:

2,500A per bar

Ultimate Capacity:

4 bar limit (10,000A)

Agency Compliance
Safety:•CAN/CSA C22.2 No. 60950-1-07+•ANSI/UL 60950-1:2011

NEBS:

Level 3 certification

Alpha Technologies Services, Inc. USA: 3767 Alpha Way, Bellingham, WA 98226 Canada: 7700 Riverfront Gate, Burnaby, BC V5J 5M4Toll Free North America: +1 800 322 5742 Outside US: +1 360 647 2360 Technical Support: +1 800 863 3364
For more information visit www.alpha.com© 2020 Alpha Technologies Services, Inc. All Rights Reserved. Trademarks and logos are the property of Alpha Technologies Services, Inc.
and its affiliates unless otherwise noted. Subject to revisions without prior notice. E. & O.E.

07/2020#0470108-00 REV E2