Monitoring Spreadsheet: JCM_ID_AM002_ver02.0
Reference Number: ID004

Monitoring Report Sheet (Input Sheet) [For Verification]
Table 1: Parameters monitored ex post
(a)
(b)
(c)
(d)
Monitoring Monitoring
Description ofParameters
periodpoint No.
data

2014/12/20
2014/12/31

2014/12/20
2014/12/31

2014/12/20
2014/12/31

(1)

(2)

(3)

(e)
MonitoredValues

(f)
Units

ECPJ,i,pPower
consumption ofproject chiller iduring the periodp

EIgrid,pElectricity
imported fromthe grid to theproject site
during the period
p1,677.365 MWh/phgen,pOperating timeof captive
electricitygenerator during
the period p

0 hours/p

60.952 MWh/p(g)
Monitoring
option(h)(i)

Source of data

Measurement methods and procedures(j)Monitoring
frequency(k)
Othercomments

Data is measured by measuring equipments in the factory.
- Specification of measuring equipments：
1) Electrical power meter is applied for measurement ofelectrical power consumption of project chiller.
2) Meter is certified in compliance with national/international
standards on electrical power meter.
- Measuring and recording：1) Measured data is automatically sent to a server where data isrecorded and stored. Measured data is manually recorded byresponsible staff for calculation of emission reduction.
Continuously2) Recorded data is checked its integrity once a month byresponsible staff.
The accuracy level of electric meter is ±0.5%.
The data monitored and required for verification and issuance will
be kept and archived electronically for two years after the final
issuance of credits.
- Calibration：
Calibration was conducted by the Manufacturer at the time ofManufacturer's inspection. Next calibration is required after 10years.

The data ofenergy
consumption of theprojectchiller tocalculate theemission
reductionamountapplies themanual
recordeddata ofmeter.

Option C

Monitored data

Option B orOption C

Invoice from thepower company [for Option B]
for Option B or Data is collected and recorded from invoices from the powermonitored data company.
for Option C

Every month

Option C

Monitored data

Continuously

II-1

Data is measured by meter equipped to a generator.

Table 2: Project-specific parameters fixed ex ante
(a)

(b)

(c)

(d)

(e)

(f)

Parameters

Description of data

EstimatedValues

Units

Source of data

Other commentsThe most recent value available at the time of validation is applied and fixed for the monitoring
period thereafter. The data is sourced from “Emission Factors of Electricity Interconnection
Systems”, National Committee on Clean Development Mechanism Indonesian DNA for CDM
unless otherwise instructed by the Joint Committee.

EFelec[For grid electricity]
CO2 emission factor for
consumed electricity

0.843 tCO2/MWh

EFelec[For captive electricity]
CO2 emission factor for
consumed electricity

0.8 tCO2/MWh

CDM approved small scale methodology: AMS-I.A

Tcooling-out,iOutput cooling watertemperature of project chiller i
set under the project specificcondition

36.9 degree Celsius

Specifications of project chiller i prepared for the quotation or factory acceptance test data by
manufacturer

Tchilled-out,iOutput chilled watertemperature of project chiller i
set under the project specificcondition

11 degree Celsius

Specifications of project chiller i prepared for the quotation or factory acceptance test data by
manufacturer

COPRE,i

COP of reference chiller iunder the standardizing
temperature conditions

5.59 -

Selected from the default values set in the methodology

COPPJ,i

COP of project chiller i underthe project specific conditions

7.14 -

Specifications of project chiller i prepared for the quotation or factory acceptance test data bymanufacturer

COPPJ,tc,i

COP of project chiller i
calculated under thestandardizing temperature
conditions

6.25 -

Calculated with the following equation;
COPPJ,tc,i= COPPJ,i × [(Tcooling-out,i - Tchilled-out,i + TDchilled + TDcooling) ÷ (37 - 7 + TDchilled + TDcooling)]

RCgen

Rated capacity of generator

0.0 kW

Specification of generator for captive electricity

Table3: Ex-post estimation of CO2 emission reductions
CO2 emission reductions
Monitoring PeriodUnits
6 tCO2/p
2014/12/20-2014/12/31[Monitoring option]
Based on public data which is measured by entities other than the project participants (Data used:Option A
Based on the amount of transaction which is measured directly using measuring equipments (DataOption B
Based on the actual measurement using measuring equipments (Data used: measured values)
Option C

II-1

In the project, there is nogenerator for captive
electricity.

Monitoring Spreadsheet: JCM_ID_AM002_ver02.0
Reference Number: ID004
Monitoring Report Sheet (Calculation Process Sheet) [For Verification]
1. Calculations for emission reductions

Fuel type

Emission reductions during the period p
2. Selected default values, etc.
COP of reference chiller i under the standardizing temperature
conditions

Value

N/A

6.07

Units
tCO2/pParameter
ERp

N/A

5.59

-COPRE,i

N/A

57.45

tCO2/pREp

3. Calculations for reference emissions
Reference emissions during the period p
Reference emissions
CO2 emission factor for consumed electricity [grid]

N/AElectricity

0.84

tCO2/MWh

EFelecElectricity

0.8

tCO2/MWh

EFelecProportion of grid electricity over total electricity
consumed at the project site

N/A

1.00

--

Proportion of captive electricity over total electricity
consumed at the project site

N/A

0.00

-

-

CO2 emission factor for consumed electricity [captive]

Electricity

60.95

MWh/p

ECPJ,i,p

COP of reference chiller i under the standardizing
temperature conditions

N/A

5.59

-

COPRE,i

COP of project chiller i calculated under thestandardizing temperature conditions

N/A

6.25

-

COPPJ,tc,i

N/A

51.38

tCO2/pPEpPower consumption of project chiller i

4. Calculations of the project emissions
Project emissions during the period p
Project emissions
CO2 emission factor for consumed electricity [grid]

N/AElectricity

0.84

tCO2/MWh

EFelecElectricity

0.8

tCO2/MWh

EFelecProportion of grid electricity over total electricity
consumed at the project site

N/A

1.00

-

-

Proportion of captive electricity over total electricity
consumed at the project site

N/A

0.00

-

-

Electricity

60.95

MWh/p

ECPJ,i,p

CO2 emission factor for consumed electricity [captive]

Power consumption of project chiller i[List of Default Values]
COPRE,i (x<300USRt)

4.92-

COPRE,i (300≤x<450USRt)

5.33

-

COPRE,i (450≤x<500USRt)

5.59

-

COPRE,i (500≤x<700USRt)

5.85

-

COPRE,i (700≤x<1250USRt)

5.94

-

TDcooling

1.50

degree Celsius

TDchilled

1.50

degree Celsius

II-2

Monitoring Spreadsheet: JCM_ID_AM002_ver02.0
Reference Number: ID004

Monitoring Report Sheet (Input Sheet) [For Verification]
Table 1: Parameters monitored ex post
(a)
(b)
(c)
(d)
Monitoring Monitoring
Description ofParameters
periodpoint No.
data

2015/1/12015/12/31

2015/1/12015/12/31

2015/1/12015/12/31

(1)

(2)

(3)ECPJ,i,pPowerconsumption ofproject chiller iduring the periodp(e)MonitoredValues

(f)
Units

1,673.745 MWh/p(g)Monitoring
option(h)(i)

Source of data

Measurement methods and procedures(j)Monitoring
frequency(k)
Othercomments

Data is measured by measuring equipments in the factory.
- Specification of measuring equipments：
1) Electrical power meter is applied for measurement ofelectrical power consumption of project chiller.
2) Meter is certified in compliance with national/international
standards on electrical power meter.
- Measuring and recording：1) Measured data is automatically sent to a server where data isrecorded and stored. Measured data is manually recorded byresponsible staff for calculation of emission reduction.
Continuously2) Recorded data is checked its integrity once a month byresponsible staff.
The accuracy level of electric meter is ±0.5%.
The data monitored and required for verification and issuance will
be kept and archived electronically for two years after the final
issuance of credits.
- Calibration：
Calibration was conducted by the Manufacturer at the time of
Manufacturer's inspection. Next calibration is required after 10years.

The data ofenergy
consumptio
n of theprojectchiller tocalculate theemission
reductionamountapplies themanual
recordeddata ofmeter.

Option C

Monitored data

EIgrid,pElectricity
imported fromthe grid to the48,936.544 MWh/pproject site
during the periodpOption B orOption C

Invoice from thepower company [for Option B]
for Option B or Data is collected and recorded from invoices from the powermonitored data company.
for Option C

Every monthhgen,pOperating timeof captive
electricity
generator during
the period p

Option C

Monitored data

Continuously

0 hours/p

II-1

Data is measured by meter equipped to a generator.

Table 2: Project-specific parameters fixed ex ante(a)

(b)

(c)

(d)

(e)

(f)

Parameters

Description of data

Estimated
ValuesUnits

Source of data

Other comments

The most recent value available at the time of validation is applied and fixed for the monitoring
period thereafter. The data is sourced from “Emission Factors of Electricity Interconnection
Systems”, National Committee on Clean Development Mechanism Indonesian DNA for CDM
unless otherwise instructed by the Joint Committee.

EFelec[For grid electricity]
CO2 emission factor for
consumed electricity

0.843 tCO2/MWhEFelec[For captive electricity]
CO2 emission factor for
consumed electricity

0.8 tCO2/MWh

CDM approved small scale methodology: AMS-I.A

Tcooling-out,iOutput cooling watertemperature of project chiller i
set under the project specificcondition

36.9 degree Celsius

Specifications of project chiller i prepared for the quotation or factory acceptance test data by
manufacturer

Tchilled-out,iOutput chilled watertemperature of project chiller i
set under the project specificcondition

11 degree Celsius

Specifications of project chiller i prepared for the quotation or factory acceptance test data bymanufacturer

COPRE,i

COP of reference chiller iunder the standardizing
temperature conditions

5.59 -

Selected from the default values set in the methodology

COPPJ,i

COP of project chiller i under
the project specific conditions

7.14 -

Specifications of project chiller i prepared for the quotation or factory acceptance test data by
manufacturer

COPPJ,tc,i

COP of project chiller i
calculated under thestandardizing temperature
conditions

6.25 -

Calculated with the following equation;
COPPJ,tc,i= COPPJ,i × [(Tcooling-out,i - Tchilled-out,i + TDchilled + TDcooling) ÷ (37 - 7 + TDchilled + TDcooling)]

RCgen

Rated capacity of generator

0.0 kW

Specification of generator for captive electricity

Table3: Ex-post estimation of CO2 emission reductions
CO2 emission reductions
Monitoring PeriodUnits
2015/1/1-2015/12/31
166 tCO2/p[Monitoring option]
Based on public data which is measured by entities other than the project participants (Data used:Option A
Based on the amount of transaction which is measured directly using measuring equipments (DataOption B
Based on the actual measurement using measuring equipments (Data used: measured values)
Option CII-1

In the project, there is nogenerator for captiveelectricity.

Monitoring Spreadsheet: JCM_ID_AM002_ver02.0
Reference Number: ID004
Monitoring Report Sheet (Calculation Process Sheet) [For Verification]
1. Calculations for emission reductions

Fuel type

Emission reductions during the period p
2. Selected default values, etc.
COP of reference chiller i under the standardizing temperature
conditions

Value

N/A

166.59Units
tCO2/pParameter
ERp

N/A

5.59

-COPRE,iN/A

1577.56tCO2/p

REp

3. Calculations for reference emissions
Reference emissions during the period p
Reference emissions
CO2 emission factor for consumed electricity [grid]

N/AElectricity

0.84

tCO2/MWh

EFelecElectricity

0.8

tCO2/MWh

EFelecProportion of grid electricity over total electricity
consumed at the project site

N/A

1.00

--

Proportion of captive electricity over total electricity
consumed at the project site

N/A

0.00

--

MWh/p

ECPJ,i,p

CO2 emission factor for consumed electricity [captive]

Power consumption of project chiller i

Electricity

1673.75

COP of reference chiller i under the standardizing
temperature conditions

N/A

5.59

-

COPRE,i

COP of project chiller i calculated under thestandardizing temperature conditions

N/A

6.25

-

COPPJ,tc,i

N/A

1410.97

tCO2/pPEp

4. Calculations of the project emissions
Project emissions during the period p
Project emissions
CO2 emission factor for consumed electricity [grid]

N/AElectricity

0.84

tCO2/MWh

EFelecElectricity

0.8

tCO2/MWh

EFelecProportion of grid electricity over total electricity
consumed at the project site

N/A

1.00--

Proportion of captive electricity over total electricity
consumed at the project site

N/A0.00--MWh/p

ECPJ,i,p

CO2 emission factor for consumed electricity [captive]

Power consumption of project chiller iElectricity

1,673.75[List of Default Values]
COPRE,i (x<300USRt)

4.92

-

COPRE,i (300≤x<450USRt)

5.33

-

COPRE,i (450≤x<500USRt)

5.59

-

COPRE,i (500≤x<700USRt)

5.85

-

COPRE,i (700≤x<1250USRt)

5.94

-

TDcooling

1.50

degree Celsius

TDchilled

1.50

degree Celsius

II-2

Monitoring Spreadsheet: JCM_ID_AM002_ver02.0
Reference Number: ID004Monitoring Report Sheet (Input Sheet) [For Verification]
Table 1: Parameters monitored ex post
(a)
(b)
(c)
(d)
Monitoring Monitoring
Description ofParameters
periodpoint No.
data

2016/1/12016/5/31

2016/1/12016/5/31

2016/1/12016/5/31

(1)

(2)

(3)

ECPJ,i,pPower
consumption ofproject chiller iduring the periodp(e)MonitoredValues

(f)
Units

851.434 MWh/p(g)
Monitoring
option(h)(i)

Source of data

Measurement methods and procedures(j)Monitoring
frequency(k)Othercomments

Data is measured by measuring equipments in the factory.
- Specification of measuring equipments：
1) Electrical power meter is applied for measurement ofelectrical power consumption of project chiller.
2) Meter is certified in compliance with national/international
standards on electrical power meter.
- Measuring and recording：1) Measured data is automatically sent to a server where data isrecorded and stored. Measured data is manually recorded byresponsible staff for calculation of emission reduction.
Continuously
2) Recorded data is checked its integrity once a month byresponsible staff.
The accuracy level of electric meter is ±0.5%.
The data monitored and required for verification and issuance will
be kept and archived electronically for two years after the final
issuance of credits.
- Calibration：
Calibration was conducted by the Manufacturer at the time of
Manufacturer's inspection. Next calibration is required after 10years.

The data ofenergy
consumptio
n of theprojectchiller tocalculate theemission
reductionamountapplies themanual
recordeddata ofmeter.

Option C

Monitored data

EIgrid,pElectricity
imported fromthe grid to the21,200.624 MWh/pproject site
during the periodpOption B orOption CInvoice from thepower company [for Option B]
for Option B or Data is collected and recorded from invoices from the powermonitored data company.
for Option C

Every monthhgen,pOperating timeof captive
electricity
generator during
the period pOption C

Monitored data

Continuously

0 hours/p

II-1

Data is measured by meter equipped to a generator.

Table 2: Project-specific parameters fixed ex ante
(a)

(b)

(c)

(d)

(e)

(f)

Parameters

Description of data

Estimated
ValuesUnits

Source of data

Other comments

The most recent value available at the time of validation is applied and fixed for the monitoring
period thereafter. The data is sourced from “Emission Factors of Electricity Interconnection
Systems”, National Committee on Clean Development Mechanism Indonesian DNA for CDM
unless otherwise instructed by the Joint Committee.

EFelec[For grid electricity]
CO2 emission factor for
consumed electricity

0.843 tCO2/MWh

EFelec[For captive electricity]
CO2 emission factor for
consumed electricity

0.8 tCO2/MWh

CDM approved small scale methodology: AMS-I.A

Tcooling-out,iOutput cooling watertemperature of project chiller i
set under the project specificcondition

36.9 degree Celsius

Specifications of project chiller i prepared for the quotation or factory acceptance test data by
manufacturer

Tchilled-out,iOutput chilled watertemperature of project chiller i
set under the project specificcondition

11 degree Celsius

Specifications of project chiller i prepared for the quotation or factory acceptance test data by
manufacturer

COPRE,i

COP of reference chiller iunder the standardizing
temperature conditions

5.59 -

Selected from the default values set in the methodology

COPPJ,i

COP of project chiller i underthe project specific conditions

7.14 -

Specifications of project chiller i prepared for the quotation or factory acceptance test data bymanufacturer

COPPJ,tc,i

COP of project chiller i
calculated under thestandardizing temperature
conditions

6.25 -Calculated with the following equation;
COPPJ,tc,i= COPPJ,i × [(Tcooling-out,i - Tchilled-out,i + TDchilled + TDcooling) ÷ (37 - 7 + TDchilled + TDcooling)]

RCgen

Rated capacity of generator

0.0 kW

Specification of generator for captive electricity

Table3: Ex-post estimation of CO2 emission reductions
CO2 emission reductions
Monitoring PeriodUnits
2016/1/1-2016/5/31
84 tCO2/p[Monitoring option]
Based on public data which is measured by entities other than the project participants (Data used:Option A
Based on the amount of transaction which is measured directly using measuring equipments (DataOption B
Based on the actual measurement using measuring equipments (Data used: measured values)
Option C

II-1

In the project, there is nogenerator for captive
electricity.

Monitoring Spreadsheet: JCM_ID_AM002_ver02.0
Reference Number: ID004
Monitoring Report Sheet (Calculation Process Sheet) [For Verification]
1. Calculations for emission reductions

Fuel type

Emission reductions during the period p
2. Selected default values, etc.
COP of reference chiller i under the standardizing temperature
conditions

Value

N/A

84.74

Units
tCO2/pParameter
ERp

N/A

5.59

-COPRE,i

N/A

802.50tCO2/pREp

3. Calculations for reference emissions
Reference emissions during the period p
Reference emissions
CO2 emission factor for consumed electricity [grid]

N/AElectricity

0.84

tCO2/MWh

EFelecElectricity

0.8

tCO2/MWh

EFelecProportion of grid electricity over total electricity
consumed at the project siteN/A

1.00

--

Proportion of captive electricity over total electricity
consumed at the project site

N/A

0.00

--

CO2 emission factor for consumed electricity [captive]

Electricity

851.43

MWh/p

ECPJ,i,p

COP of reference chiller i under the standardizing
temperature conditions

N/A

5.59

-

COPRE,i

COP of project chiller i calculated under thestandardizing temperature conditions

N/A

6.25

-

COPPJ,tc,i

N/A

717.76tCO2/pPEpPower consumption of project chiller i

4. Calculations of the project emissions
Project emissions during the period pProject emissionsCO2 emission factor for consumed electricity [grid]

N/AElectricity

0.84

tCO2/MWh

EFelecElectricity

0.8

tCO2/MWh

EFelecProportion of grid electricity over total electricity
consumed at the project site

N/A

1.00

-

-

Proportion of captive electricity over total electricity
consumed at the project site

N/A

0.00

-

-

Electricity

851.43

MWh/p

ECPJ,i,p

CO2 emission factor for consumed electricity [captive]

Power consumption of project chiller i[List of Default Values]
COPRE,i (x<300USRt)

4.92

-

COPRE,i (300≤x<450USRt)

5.33

-

COPRE,i (450≤x<500USRt)

5.59

-

COPRE,i (500≤x<700USRt)

5.85

-

COPRE,i (700≤x<1250USRt)

5.94

-

TDcooling

1.50

degree Celsius

TDchilled

1.50

degree Celsius

II-2