High Pressure Fog
High Pressure Fog

外形尺寸图（主机部） External View (Main Unit)High Pressure Humidification System

UruOs-50,UruOs-50RO 共通
UruOs-50, UruOs-50RO Common Size

高压加湿器 UruOs 50

产品的规格·外观变更时不予事先通知。
Specification may be changed without notice.

外形尺寸图（喷雾部） External View (Spraying Unit)

3.0L/h喷雾型,5.0L/h喷雾型 共通
3.0L/h Spray-type, 5.0L/h Spray-type

Common Size

Ur uOs UNI

http://www.cosmotech-jp.com

E-mail: KYOTO@ cosmotech-jp.com

12-2 Fukakusa Zendoji-Cho, Fushimi-ku, Kyoto, 612-8433, Japan

Tel: +81 75 621 7431 Fax: +81 75 621 7473

产品的规格·外观变更时不予事先通知。
Specification may be changed without notice.

Registered establishment: Cosmotech Co., Ltd. headquarters and Kyoto Factory.
Registered coverage: Design, development, manufacturing, sales, installation and maintenance of peripheral equipments forller,

1509-CH/E

Distributor

Flow Diagram系统流程图反渗透膜过滤(RO)纯水装置一体型高压加湿器
High Pressure Humidification System with Built-in RO System

湿度传感器用电缆Humidity Sensor Cable

UruOs 50 是 COSMOTECH 公 司 经 过 长 年 对 高 压 方 式
加湿器的交货实绩以及经验，独自研发提案的新产品。
小型且性价比优越的装置，确信在经济性·卫生方面必定得到高度的评价。

风扇用电缆Fan Cable

UruOs 50 is high pressure humidification system which is based on
atomizing water using pressure.
This system produces a fine fog-likemist for easy absorption.
High pressure humidification system
is very inexpensive to operate and is
low maintenance.

特长Feature

省电清洁

●

●

因为不使用空气压缩机，加湿时只需要很少的电力消耗。

●只需主机(泵部)的设置空间「550mm×550mm」，省空间。
Installation space is space-saving as the main unit (pump part) is “550mm×550mm”.

Space-saving●维护简单维护保养是定期交换水滤芯·UV 灯和进行泵的点检(运转时间约2000/4000)
Maintenances are periodical replacement of a water filter and a UV lamp and checkof a pump at every approx. 2000/4000 operating hours.

Easy Maintenance●●音给「UruOs 50」主机电源(200V)通电，并供水。用高压管和风扇用电缆连接喷头「UruOs UNI」。
湿度传感器是把室内的湿度设置到需要的点，连接湿度传感器用电缆。设定好希望的湿度后，自动控制。
Power supply (200V) and water supply are connected to the main unit "UruOs 50", and high pressure
hoses and fan cables are connected to spraying units "UruOs UNI".
A humidity sensor is installed at the place which needs humidification, and connected a humidity sensor
cable. Humidity is set up and automatic control is performed.

规格一览Specifications
主机部项Comparison with Other Systems

目Item经济性 ( 电费 )Economy (Electric Charge)

消耗电力 ( 水 1L/h)
Power Consumption (1L/h)

冷却效果Cooling Effect

维护费用Maintenance Cost压 缩机Compressor

噪 音Noise设置空间
Installation Space系 统 密闭 度System Sealing细菌繁殖防止Prevention from Bacteria

卫 生
HygieneUruOs 50○
8 ～ 10W
○

压缩机式

Steam

Vaporizer

Compressor

×600 ～ 800W

××60 ～ 80W○×30 ～ 50W
○△×△

×

不要

不要

不要要

Not Necessary

Not Necessary

Necessary

Not Necessary○○○○○○×○○△△×××××△△△△评价…… 优○ 中△ 差×
Evaluation......Good ○ Moderate△ Bad×部

Spraying Part

名称高压加湿器

名称

喷头High Pressure Humidification System

Name

Spraying Unit

加湿能力气化式雾Name

UruOs 50

Model

蒸汽式

喷Main Part形式

其他方式和比较我们平常使用的水中含有矿物质成分（钙，镁等），向空气中喷雾时，会析出矿物粉末（白粉）。
使用地下水等特别是含量多的水（硬水）时，这种现象表现的更为明显。
电子零件，精密机器，计算机室，印刷表面加工，食品工业等需要特别注意。
另外，这种矿物质成分还可能造成喷嘴的堵塞。
反渗透膜过滤（RO）纯水装置一体型的 UruOs-50RO 能过滤掉 99% 的矿物质成分，可以用过滤后的纯水进行喷雾。
Mineral ingredient (calcium, magnesium and etc.) is in the water, and when spraying water in the air,it's separated out as mineral dust (powder). Hard water has high mineral ingredient contents, and thephenomenon is found conspicuously. Electronic parts, precision mechanical equipment, a computerroom, printed paper surface coating and food industry are required special care in particular. There isalso a possibility which causes a nozzle clogging by this mineral ingredient. The high pressure humidification system with built-in RO membrane filtration system can remove 99% of mineral ingredient and spray the deionized water.

规格一览Specifications

名 称

RO 装置一体型高压加湿器

Description of ProductHigh Pressure Humidification System with Built-in RO System

形 式

UruOs-50ROModel

加湿能力Humidification Capacity

因为不喷出空气，所以非常安静，办公室等都可以设置。
Since air is not spewed, noise level is very low and the installation to an office etc.
is also possible.

SilentFine spraying by High Pressure System

排水DrainUruOs UNI 最大可以安装16台(1.5L/h×2个)。可以进行广范围的加湿。
Installation of a maximum of 16 sets of spraying unit UruOs UNI (1.5Lh×2 nozzles)
is possible, and it can perform extensive humidification.

Extensive Humidification

高压细微喷雾预滤器
Pre-filter

和自来水直接连接喷雾，通过UV(紫外线杀菌)灯(※选配)防止霉和细菌的发生。
It is connected to water service and sprays water directly. Generating of mold orbacteria is barred by passing water through UV lamp (option).

Hygiene广范围加湿高压管High Pressure Hose电源Power Supply

Since an air compressor is not used, it can humidify by little power consumption.

省空间

UruOs UNI给水
Water Supply

Power Saving

静UruOs 50

湿度传感器
Humidity Sensor

Humidification Capability

Min10L/h ～ Max50L/h

形式
Model

UruOs UNI喷雾量约3.0L/h(1.5L/h×2)∕约5.0L/h(2.5L/h×2)

Amount of Spraying

3.0L/h(1.5L/h×2) / 5.0L/h(2.5L/h×2)

湿度表示·设定

数字表示·设定(0 ～ 100%)

风扇最大风量Humidity Display・Setting

Digital Display・Setting(0~100%)

Fan Max. Air Volume

湿度检知半导体式湿度传感器风扇最大静压

Humidity Detection

Humidity Sensor Semiconductor TypeFan Max. Static Pressure

控制方式

2阶段时间控制方式

风扇噪音Control MethodTwo-step Spraying Duration Control

Fan Noise

37∕41 db泵过电流

风扇平均寿命50,000 小时

Fan Product Lifetime

Average 50,000 Hours

检知·保护机能给水压力低下

连接台数合计 50L/h以内 (最低10L/h)

Protection Function

Water Supply Low Pressure

No. of Connection

Less than Amount of Sum Total Spraying 50L/H (Minimum 10L/H)

给水温度上升(40℃)

外径 8.3(mm) × 内径 1/8(in)Water Supply High Temperature (40℃)

Size: OD 8.3 (mm) ID 1/8 (inch)

加压泵

0.4KW

50/60Hz选配UV杀菌装置Option

UV Sterilization Device

Max使用压力 : 20Mpa
连接管子Connection Hose

数字表示·设定 (0 ～ 100％)
Digital Display and Setting (0~100%)湿度检知

半导体式湿度传感器Humidity Detection

Semiconductor Humidity Sensor

控制方式

2 阶段时间控制方式

Control MethodTwo-step Spraying Duration Control

加压泵

0.4ＫＷ

Pressurized Pump

50/60Hz杀菌机能UV 杀菌装置 ( 标准配备 )Sterilization Function

UV Sterilization Device (Standard Equipment)

RO 装置

筒式 RO 滤芯 (6 支 )RO System

Cartridge Type RO Filter (6 pcs)

RO 处理能力Approx. 90L/h (At 25°
C/ Using 6 PCS)

约 90Ｌ/ｈ(25℃/6 支 使用时 )RO Processing Capacity

约 56Ｌ/ｈ(10℃/6 支 使用时 )Approx. 56L/h (At 10°
C/ Using 6 PCS)

Pump Over-current

Pressurized Pump

湿度表示·设定
Humidity Indication and Setting

2.5∕2.9 m³/min
64.8∕76.5 Pa

Min10L/h ～ Max50L/h

Max. Operation Pressure: 20MPa

Min破坏压力 : 72Mpa
Min. Burst Pressure: 72MPa

电源

3φ200VPower Supply

约 3.5A约 1.2KVA

3φ200V / Approx. 3.5A / Approx. 1.2KVA

外形尺寸
Dimensions(mm)W550×D550×H1085※检知·保护机能和 UruOs-50 为共通规格。
*Detection and protective function are the same specification as UruOs-50.

自来水中含有的残留氯会对 RO（返渗透膜）纯水的产生造成阻碍。
为了延长RO滤芯的使用寿命，请和活性炭滤芯一起使用。

Residual chlorine contained in tap water affects deionized water generation of RO system. Installation ofan activated carbon filter is highly recommended to extend lifetime of RO filters.

电源3φ200V 约3A 约1.1KVA

最小弯曲半径 : 15mm

Power Supply

3φ200V / Approx. 3A / Approx. 1.1KVA

Min. Bend Radius: 15mm

交换时期1φ200V 140/120 mA1μ滤芯（L500）······ 6个月

1 µ filtration filter (L500) ..... Every 6 Months

活性炭滤芯（L500）··· 6个月

Activated Carbon Filter (L500) ..... Every 6 Months

外形尺寸
Dimensions (mm)W550×D550×H1085

制品的规格·外观变更时不另行通知。

Specification and appearance of a product are subject to change without notice.

电源Power Supply

外形尺寸
Dimensions (mm)W123.4×D203×H200

Estimated Timing for Exchange of Filters

筒式RO滤芯········ 1年（6支同时交换） Cartridge Type RO Filter ..... Once a Year (6 Filters Simultaneous Exchange)