R

Netvox LoRa Sensors & Devices
Wireless Sensor Network Based on LoRa Technology

Product Catalogue2024

Intellectual System Based on LoRa Technology

What is LoRa?
LoRa technology was developed by a company called Semtech and it is a newwireless protocol designed specifically for long-range, low-power
communications. LoRa stands for Long Range Radio and is mainly targeted forM2M and IoT networks. This technology will enable public or multi-tenant
networks to connect a number of applications running on the same network.

LoRa Alliance was formed to standardize LPWAN (Low Power Wide Area
Networks) for IoT and is a non-profit association which features membershipfrom a number of key market shareholders such as CISCO, Actility, MicroChip,
IBM, STMicro, SEMTECH, Orange mobile and many more. This alliance is key toproviding interoperability among multiple nationwide networks.

Each LoRa gateway has the ability to handle up to millions of nodes. The
signals can span a significant distance, which means that there is lessinfrastructure required, making constructing a network much cheaper andfaster to implement.

LoRa also features an adaptive data rate algorithm to help maximize the nodes
life and network capacity. The LoRa protocol includes a number of different
layers including encryption at the network, application and device level for
secure communications.

2Intellectual System Based on LoRa Technology
Where does LPWAN fit?
One technology cannot serve all of the projected applications and volumes for
IoT. Wi-Fi and BTLE are widely adopted standards and serve the applications
related to communicating personal devices quite well. Cellular technology is agreat fit for applications that need high data throughput and have a powersource. LPWAN offers multi-year lifetime and is designed for sensors andapplications that need to send small amounts of data over long distances a few
times per hour from varying environments.

Important Factors in LPWAN?
The most critical factors in a LPWAN are:⚫

Network architecture⚫

Communication range⚫

lifetime or low power⚫

Robustness to interference⚫

Network capacity (maximum number of nodes in a network)⚫

Network security⚫

One-way vs two-way communication⚫

Variety of applications served

Reference: https://docs.wixstatic.com/ugd/eccc1a_ed71ea1cd969417493c74e4a13c55685.pdf

3Intellectual System Based on LoRa Technology
What is LoRaWAN ?
LoRaWAN defines the communication protocol and system architecture forthe network while the LoRa® physical layer enables the long-range
communication link. The protocol and network architecture have the mostinfluence in determining the lifetime of a node, the network capacity, thequality of service, the security, and the variety of applications served by the
network.
Application
LoRa® MACClass A
(Baseline)

Class B
(Beacon)Class C(Continuous)

EU868

LoRa® Modulation
US915
AU915
AS923

…

MAC options
Regional ISM band

Network Architecture

Many existing deployed networks utilize a mesh network architecture. In amesh network, the individual end-nodes forward the information of othernodes to increase the communication range and cell size of the network.

4
Reference: https://docs.wixstatic.com/ugd/eccc1a_ed71ea1cd969417493c74e4a13c55685.pdf

Intellectual System Based on LoRa Technology
Netvox Network Architecture
While this increases the range, it also adds complexity, reduces network capacity,and reduces lifetime as nodes receive and forward information from other nodes
that is likely irrelevant for them. Long range star architecture makes the most sense

for preserving lifetime when long-range connectivity can be achieved.

In a LoRaWAN

network nodes are not associated with a specific gateway. Instead,data transmitted by a node is typically received by multiple gateways. Each gateway
will forward the received packet from the end-node to the cloud-based network server

via some backhaul (either cellular, Ethernet, satellite, or Wi-Fi).

The intelligence and complexity is pushed to the network server, which manages the
network and will filter redundant received packets, perform security checks, schedule
acknowledgments through the optimal gateway, and perform adaptive data rate, etc.

If a node is mobile or moving there is no handover needed from gateway
to gateway, which is a critical feature to enable asset tracking applications–a major
target application vertical for IoT.
Reference: https://docs.wixstatic.com/ugd/eccc1a_ed71ea1cd969417493c74e4a13c55685.pdf

5Intellectual System Based on LoRa Technology
LoRaWAN Regional Summery
The LoRaWAN specification varies slightly from region to region based on
the different regional spectrum allocations and regulatory requirements. The

LoRaWAN specification for Europe and North America are defined, butother regions are still being defined by the technical committee.

Joining the LoRa® Alliance as a contributor member and participating in thetechnical committee can have significant advantages to companies targeting
solutions for the Asia market.

6
Reference: https://docs.wixstatic.com/ugd/eccc1a_ed71ea1cd969417493c74e4a13c55685.pdf

Intellectual System Based on LoRa Technology
LoRaWAN Features

Long Range

Max Lifetime

1. Greater than cellular
2. Deep indoor coverage
3. Star topology

4. Low power optimized
5. Long lifetime
6. >10x vs cellular M2M

Multi-Usage

Low Cost

7. High capacity
8. Multi-tenant
9. Public network

10. Minimal infrastructure
11. Low cost end node
12. Open SW
7

Reference: https://docs.wixstatic.com/ugd/eccc1a_ed71ea1cd969417493c74e4a13c55685.pdf

Table of Contents
Model
Gateway
R206
R206A
R206C
R207
R207C

R309
R311A/R313A
R311D/R313D
R311DA/R313DA
R311DB/R313DB
R311W/R313W
R312/R313M
R312A/R313MA
R315 Series
R602A/R602B
R603
R718DA/R718DA2
R718DB/R718DB2
R718F/R718F2
R718T/R718T2
R718TB
RA02A
RA02C
RA02D1RA02G
RB11E
R311B/R313B
R311CA/R313CA
R311CB/R313CB
R311CC/R313CC
R311G/R313G

Description
Wireless IoT Controller
Wireless Dual-Mode IoT Controller
Wireless IoT Controller with External Antenna
Wireless IoT Controller
Wireless IoT Controller with External Antenna
Wireless Wearable Emergency Button with Inactivity
Detection
Wireless Door/Window Sensor
Wireless Asset Sensor
Wireless Vibration Sensor, Rolling Ball Type
Wireless Vibration Sensor, Spring Type
Wireless 2-Gang Water Leak Detector
Wireless Door Bell Button
Wireless Emergency Button
Wireless Multifunction Sensor
Wireless Siren
Wireless Customized Voice Announcer
Wireless 1-Gang/2-Gang Vibration Sensor, Rolling Ball Type
Wireless 1-Gang/2-Gang Vibration Sensor, Spring Type
Wireless 1-Gang/2-Gang Reed Switch Open/Close Detection
SensorWireless 1-Input/2-Input Push Button Interface
Wireless Push Button
Wireless Smoke Detector
Wireless CO Detector
Wireless Liquefied Petroleum Gas Detector
Wireless Cigarette Smoke, Vaping and Bullying Alarm
SensorWireless Occupancy / Light / Temperature Sensor
Wireless Light Sensor
Wireless 2-Input Dry Contact Interface
Wireless Window Sensor with Glass Break Detector
Wireless 2-Gang Door/Window Sensor
8
Wireless Light Sensor

Table of Contents
Model
Gateway

Description

R311K/R313K
R311LA/R313LA
R311WA/R313WA
R711
R712

Wireless Tilt Sensor
Wireless Infrared Proximity Sensor
Wireless 2-Gang Seat Occupancy Sensor
Wireless Temperature and Humidity Sensor
Wireless Outdoor Temperature and Humidity Sensor
Wireless Temperature and Humidity Sensor For Low
Temperature Environment
Wireless Temperature and Humidity Sensor
Wireless Temperature Sensor
Wireless Temperature Sensor - PT1000 Clamp Probe
Wireless Temperature Sensor - PT1000 Patch Probe
Wireless 1-Gang/2-Gang Temperature Sensor
Wireless 1-Gang/2-Gang Temperature Sensor
Wireless 1-Gang/2-Gang Temperature Sensor
Wireless 1-Gang/2-Gang Temperature Sensor
Wireless 1-Gang/2-Gang Temperature Senso
Wireless 1-Gang/2-Gang Temperature Sensor
Wireless 1-Gang/2-Gang Temperature Sensor
Wireless 1-Gang/2-Gang Thermocouple Sensor - Type K
Wireless Temperature and Humidity Sensor with
Thermocouple Sensor - Type K
Wireless 1-Gang/2-Gang Thermocouple Sensor - Type N
Wireless 1-Gang/2-Gang Thermocouple Sensor - Type T
Wireless Temperature and Humidity Sensor with
Thermocouple Sensor - Type T
Wireless CO Sensor
Wireless NO Sensor
Wireless O3 Sensor
Wireless H2S Sensor
Wireless NO2 Sensor
Wireless SO2 Sensor
Wireless Noise Sensor
Wireless PH Sensor
9
Wireless Turbidity Sensor

R718A/R718A01
R718AB
R718AD
R718BC/R718BC2
R718BP/R718BP2
R718B120/R718B220
R718B121/R718B221
R718B122/R718B222
R718B140/R718B240
R718B141/R718B241
R718B150/R718B250
R718B151/R718B251
R718CK/R718CK2
R718CKAB
R718CN/R718CN2
R718CT/R718CT2
R718CTAB

R718PA1
R718PA2
R718PA3
R718PA4
R718PA5
R718PA6
R718PA7
R718PA8
R718PA10

Table of Contents
Model
Gateway

Description
R718PA11
Wireless Liquid Level Sensor
R718PA22
Wireless Bottom-installed Ultrasonic Liquid Level Sensor
Wireless Soil Moisture/Temperature/Electrical Conductivity
R718PB15/R718PB15A
Sensor
R718PE
Wireless Top-Mounted Ultrasonic Level Sensor
R718PE02/R718PE02D Wireless Lidar Material Level Detection Sensor
R718PG
Wireless Light Sensor
R718PQ
Wireless Short-Range Occupancy Sensor
R718PQA
Wireless Toilet Occupancy Sensor
Wireless CO2/Temperature/Humidity/Vibration/Air
R718UBB Series
Pressure/Light Sensor
Wireless CO2/Temperature/Humidity/Vibration/Air
R718UBD Series
Pressure/Light/TVOC/PM2.5/PM10 Sensor
R718VA
Wireless Flush Toilet /Washing Liquid Bottle/Toilet Paper
Wireless Flush Toilet /Washing Liquid Bottle/Toilet
R718VB
Paper/Non-metallic pipe
R718WA/R718WA2
Wireless 1-Gang/2-Gang Water Leak Detector
R718WAA
Wireless Water Leakage/Temperature/Humidity Sensor
Wireless 1-Gang/2-Gang Water Leak Detector with Rope
R718WB/R718WB2
SensorWireless Water Leak Detector (Rope Sensor) with
R718WBA
Temperature and Humidity Sensor
Wireless Ultrasonic Distance Sensor and Temperature
R718X
Sensor
R718Y
Wireless Differential Pressure and Temperature Sensor
R719A
Wireless Surface-Mounted Parking Sensor
R720A
Wireless Temperature and Humidity Sensor
Wireless Temperature and Humidity Sensor with Activity
R720B
Detection Sensor
R720C
Wireless Air Pressure and Temperature Sensor
R720E
Wireless TVOC / Temperature / Humidity Sensor
R720F Series
Wireless Liquid Hand Soap Sensor
R720FW
Wireless Water Leak Detector
R720FLT
Wireless Toilet Tank Leak Detector
10Table of Contents
Model
Gateway

RA0701/RA0701Y/
R72601
RA0708/RA0708Y/
R72608RA0710/RA0710Y/
R72610RA0711/RA0711Y/
R72611
RA0715/RA0715Y/
R72615/R72615A
RA0716/RA0716Y/
R72616/R72616A
RA0723/RA0723Y/
R72623RA0724/RA0724Y/
R72624
RA0730/RA0730Y/
R72630R72632A/R72632A01
RA07W
RA08B01/RA08B01S
RA08B02/RA08B02S
RA08B03/RA08B03S
RA08B04/RA08B04S
RA08D07/RA08D07S

RA08D08/RA08D08S
RA08D09/RA08D09S
R211
R311FA/R313FA
R311FA1/R313FA1

Description
Wireless CO Sensor
Wireless Water pH Sensor
Wireless Water Turbidity Sensor
Wirelessr Liquid Level Sensor

Wireless CO2 / Temperature / Humidity Sensor
Wireless PM2.5 / Temperature / Humidity Sensor
Wireless PM2.5 / Noise / Temperature / Humidity Sensor
Wireless Noise / Temperature / Humidity Sensor

Wireless Wind Speed / Wind Direction / Temperature /Humidity Sensor
Wireless Soil NPK Sensor
Wireless Water Leak Detection and Location Sensor
Wireless CO2 / Temperature / Humidity / TVOC / Light / Air
Pressure / PIR Sensor
Wireless CO2 / Temperature / Humidity / TVOC / PIR Sensor
Wireless CO2 / Temperature / Humidity / TVOC / Light / Air
Pressure / PIR / NH3 / H2S Sensor
Wireless CO2 / Temperature / Humidity / PIR / NH3 / H2S
SensorWireless CO2 / Temperature / Humidity / TVOC / Light / Air
Pressure / PIR / CH2O / CO Sensor
Wireless PM2.5 / Temperature / Humidity / TVOC / Light /Air Pressure / PIR / CO Sensor
Wireless CO2 / Temperature / Humidity / TVOC / Light / Air
Pressure / PIR / NH3 / H2S Sensor
Wireless IR BlasterWireless Activity Detection Sensor
Wireless Accelerometer11

Table of Contents
Model
Gateway

R718MA
R718MBA
R718MBB
R718MBC

Description
Wireless Activity Event Counter
Wireless Activity Timer
Portable LoRa Field Signal Meter
Wireless Accelerometer and Surface Temperature Sensor
Wireless Tilt Angle (and Surface Temperature) Sensor
Wireless 1-Input/2-Input 0-5V ADC Sampling Interface
Wireless 1-Input/2-Input 0-10V ADC Sampling Interface
Wireless 1-Input/2-Input Dry Contact Interface
Wireless 1-Input/2-Input Pulse Counter Interface
Wireless 1-Gang/2-Gang Hall Type Open/Close Detection
SensorWireless Asset Sensor
Wireless Activity Detection Sensor
Wireless Activity Event Counter
Wireless Activity Timer

R718KA/R718KA2

Wireless 1-Input/2-Input 4~20mA Current Meter Interface

R718KBA
R718KBB

Wireless 4-Input 0-10V ADC Sampling Interface
Wireless 4-Input 0-20mA Sensor Interface
Wireless 2-Input 0-10V ADC Sampling and 2-Input 0-20mA
Sensor Interface
Wireless RS485 Adapter
Wireless RS232 Adapter

R311FB/R313FB
R311FC/R313FC
R716S
R718E/R718EC
R718EA/R718EB
R718IA/R718IA2
R718IB/R718IB2
R718J/R718J2
R718H/R718H2
R718LB/R718LB2

R718KBC

R718PC
R718PDA
R718N17/
R718N17E/
R718N17D/
R718N17DE
R718N115/
R718N115E/
R718N115D/
R718N115DE
R718N125/
R718N125E/
R718N125D/
R718N125DE

Wireless Single-Phase Current Meter with 1 x 75A ClampOn CT

Wireless Single-Phase Current Meter with 1 x 150A ClampOn CT

Wireless Single-Phase Current Meter with 1 x 250A ClampOn CT
12

Table of Contents
Gateway
Model
R718N163/
R718N163E/
R718N163D/
R718N163DE
R718N1100/
R718N1100E/
R718N1100D/
R718N1100DE
R718N1300/
R718N1300E/
R718N1300D/
R718N1300DE
R718N37/
R718N37E/
R718N37D/
R718N37DE
R718N315/
R718N315E/
R718N315D/
R718N315DE
R718N325/
R718N325E/
R718N325D/
R718N325DE
R718N363/
R718N363E/
R718N363D/
R718N363DE
R718N3100/
R718N3100E/
R718N3100D/
R718N3100DE
R718N3300/
R718N3300E/
R718N3300D/
R718N3300DE

Description
Wireless Single-Phase Current Meter with 1 x 630A ClampOn CT

Wireless Single-Phase Current Meter with 1 x 1000A ClampOn CT

Wireless Single-Phase Current Meter with 1 x 3000A ClampOn CT

Wireless 3-Phase Current Meter with 3 x 75A Clamp-On CT

Wireless 3-Phase Current Meter with 3 x 150A Clamp-On CT

Wireless 3-Phase Current Meter with 3 x 250A Clamp-On CT

Wireless 3-Phase Current Meter with 3 x 630A Clamp-On CT

Wireless 3-Phase Current Meter with 3 x 1000A Clamp-On
CT

Wireless 3-Phase Current Meter with 3 x 3000A Clamp-On
CT13

Table of Contents
Model
Gateway

R718N360/
R718N360D
R718NL17/
R718NL37
R718NL115/
R718NL315
R718NL125/
R718NL325
R718NL163/
R718NL363
R718IJK

RP02RH1PN063/
RP02RH1PNLB063
RP02RH3PN063/
RP02RH3PNLB063
RP02RH2P100/
RP02RH4P100
RP02RH3P250/
RP02RH4P250
RA10
R809A/R809A01
R816B/R816B01
R831
RB02B/RB02C/RB02I
DSC100C
DSC100C4
DSC716L
R100H
R100L

Description
Wireless 3-Phase Current Meter Interface
Wireless Light Sensor and 1-Phase/3-Phase Current Meter
with 75A Clamp-On CT
Wireless Light Sensor and 1-Phase/3-Phase Current Meter
with 150A Clamp-On CT
Wireless Light Sensor and 1-Phase/3-Phase Current Meter
with 250A Clamp-On CT
Wireless Light Sensor and 1-Phase/3-Phase Current Meter
with 630A Clamp-On CT
Wireless Multi-Sensor Interface for 0-24V ADC, Dry Contact
and 4-20mA Sensors
Wireless 1P+N Miniature Circuit Breaker with Power Meter(and Leak Detection), 63A (with 30mA sensitivity)
Wireless 3P+N Miniature Circuit Breaker with Power Meter(and Leak Detection), 63A (with 30mA sensitivity)
Wireless 2P/4P Miniature Circuit Breaker with Power Meter,
100A
Wireless 3P/4P Miniature Circuit Breaker with Power Meter,
250A
Wireless Valve Controller
Wireless Plug-and-Play Power Outlet with Consumption
Monitoring (and Power Outage Detection)
Wireless Wall-Mounted Power Socket with Consumption
Monitoring (and Power Outage Detection)
Wireless Multifunctional Control Box
Wireless 1-Gang/2-Gang/3-Gang Push Button Sensor
Indoor Renewable Energy Power Bank for IoT - USB-C
VersionIndoor Renewable Energy Power Bank for IoT with 4
Lithium-ion
Illuminance Meter
Wireless LoRa Module
Wireless LoRa Module

14

Frequency Characters for All Netvox LoRa Devices
The LoRa frequency characters are shown as below. Applicable to all Netvox LoRa
Devices which are equipped with SX1276 wireless communication module.

LoRa Frequency Characters

TX Power

US915 20dbm；
AS923 16dbm；
AU915 20dbm；
CN470 19.15dbm；
EU868 16dbm；
KR920 14dbm；
IN865 20dbm；

Rx Sensitivity-136dBm(LoRa，Spreading Factor=12，Bit Rate=293bps )-121dBm(FSK, Frequency deviation=5kHz, Bit Rate=1.2kbps)

Antenna Type

Built-in antennaCommunication Range

Up to10 km, the actual transmission distance depends onthe environment.

Data Transfer Rate

0.3kbps ~ 50kbps (LoRa)
1.2kbps ~ 300kbps (FSK)

Spread Technique

LoRa/FSK

Available Frequency

EU863-870，US902-928，AU915-928，KR920-923，
AS923-1，AS923-2，AS923-3，IN865-867，CN470-510
Configured before shipment

15

R206 Wireless IoT Controller
R206 is a Cloud-Based Wireless Smart Home Controller.
As the core of the entire wireless smart IoT system,
R206 is a combination of the cloud technology, Wi-Fi,
and LoRa wireless IoT technology.
R206 connects to the Internet and combines with the
Netvox cloud service platform to achieve remotemonitoring.
※ Only used in Netvox M2 private LoRa Solution※ The LoRaWAN device is not supported

Main Characteristics
◼
◼
◼
◼
◼
◼

Support LoRa
Support Netvox cloud and Netvox M2 APP
Support 3.5G/4G USB dongle
Support RTC (Real-time clock)Support gateway / bridge / wi-fi AP mode
Two RJ-45 interfaces (WAN/LAN)

Technical Parameter
Power

Input: AC 100~240V
Output: DC 12V/1.5A

Power Consumption

2.2W (28mA @230V 50Hz) (Typical)

Dimension

124mm x 155mm x 65mm

Shell Material

PC510

Operating Temperature-10°C~50°C

Operating Humidity

0~95%RH (No condensation)

Storage Temperature-20°C~60°C

Storage Humidity

0~95%RH (No condensation)

16
Available Frequency : EU/IN Region, US/AU Region, AS Region, KR Region, CN Region

R206A Wireless Dual-Mode IoT Controller
R206A is a Cloud-Based Wireless Smart Home
Controller.
As the core of the entire wireless smart IoT system,
R206A is a combination of the cloud technology, Wi-Fi,
Zigbee and LoRa wireless IoT technology.

R206A connects to the Internet and combines with the
Netvox cloud service platform to achieve remotemonitoring.
※ Only used in Netvox M2 private LoRa Solution※ The LoRaWAN device is not supported

Main Characteristics
◼
◼
◼
◼
◼
◼

Support LoRa and ZigBee
Support Netvox cloud and Netvox M2 APP
Support 3.5G/4G USB dongle
Support RTC (Real-time clock)Support gateway / bridge / wi-fi AP mode
Two RJ-45 interfaces (WAN/LAN)

Technical Parameter
Power

Input: AC 100~240V
Output: DC 12V/1.5A

Power Consumption

2.2W (28mA @230V 50Hz) (Typical)

Dimension

124mm x 155mm x 65mm

Shell Material

PC510

Operating Temperature-10°C~50°C

Operating Humidity

0~95%RH (No condensation)

Storage Temperature-20°C~60°C

Storage Humidity

0~95%RH (No condensation)

17
Available Frequency : EU/IN Region, US/AU Region, AS Region, KR Region, CN Region

R206C Wireless IoT Controller with External Antenna
R206C is a highly reliable wireless smart cloud gateway.
As the core of the entire wireless smart IoT system,
R206C achieves the combination of cloud technology,
Wi-Fi, and Netvox LoRa. The Netvox APP (Android andiOS) can control the device. Users can also monitor allchanges in the network by accessing R206C throughthe cloud, and easily realize real IoT remote control toachieve energy saving, carbon reduction, and green
environmental protection.
※ Only used in Netvox M2 private LoRa Solution※ The LoRaWAN device is not supported

Main Characteristics
◼
◼
◼
◼
◼
◼
◼

Support LoRa
Support Netvox cloud and Netvox M2 APP
Support 3.5G/4G USB dongle
Support RTC (Real-time clock)Support gateway / bridge / wi-fi AP mode
Two RJ-45 interfaces (WAN/LAN)
External suction cup antenna

Technical Parameter
Power

Input: AC 100~240V
Output: DC 12V/1.5A

Power Consumption

2.2W (28mA @230V 50Hz) (Typical)

Dimension

124mm x 155mm x 65mm

Shell Material

PC510

Operating Temperature-10°C~50°C

Operating Humidity

0~95%RH (No condensation)

Storage Temperature-20°C~60°C

Storage Humidity

0~95%RH (No condensation)

18
Available Frequency : EU/IN Region, US/AU Region, AS Region, KR Region, CN Region

R207 Wireless IoT Controller
R207 is a Wireless IoT Controller. As the core of theentire smart home system, R207 is the first one
achieving the perfect combination of cloud technology
and Netvox LoRa proprietary protocol Internet ofThings. R207 acts as a gateway in the LoRa networkand can automatically screen and configure. The thirdparty software can control the device through R207,
for example, the Android client side can achieve mode
control. At the same time, users can monitor all thechanges of home via R207 through the cloud, realize
the remote control of smart home easily and havefunctions about energy saving, emission reduction andenvironmental protection.
※ Only used in Netvox M2 private LoRa Solution※ The LoRaWAN device is not supported

Main Characteristics◼ Support Netvox cloud and Netvox M2 APP◼ One RJ-45 interfaces (WAN)

Technical Parameter
Power

Input: AC 100~240V
Output: DC 5V/1A

Power Consumption

5V/0.12A/0.6W (typical)

Dimension

76.5mm x 37.0mm x 22.0mm

Shell Material

PC510

Operating Temperature-10°C~50°C

Operating Humidity

0~95%RH (No condensation)

Storage Temperature-20°C~60°C

Storage Humidity

0~95%RH (No condensation)

19
Available Frequency : EU/IN Region, US/AU Region, AS Region, KR Region, CN Region

R207C Wireless IoT Controller with External Antenna
R207C is a highly reliable wireless smart cloud gateway.
As the core of the entire wireless smart IoT system,
R207C achieves the combination of cloud technology
and LoRa wireless IoT technology.
The Netvox APP (Android and iOS) can control thedevice. Users can also monitor all changes in the
network by accessing R207C through the cloud, andeasily realize real IoT remote control to achieve energy
saving, carbon reduction, and green environmental
protection.
※ Only used in Netvox M2 private LoRa Solution※ The LoRaWAN device is not supported

Main Characteristics◼ Support Netvox cloud and Netvox M2 APP◼ One RJ-45 interfaces (WAN)◼ External Antenna

Technical Parameter
Power

Input: AC 100~240V
Output: DC 5V/1A

Power Consumption

5V/0.12A/0.6W (typical)

Dimension

76.5mm x 37.0mm x 22.0mm

Shell Material

PC510

Operating Temperature-10°C~50°C

Operating Humidity

0~95%RH (No condensation)

Storage Temperature-20°C~60°C

Storage Humidity

0~95%RH (No condensation)

20
Available Frequency : EU/IN Region, US/AU Region, AS Region, KR Region, CN Region

R309 Wireless Wearable Emergency Button with Inactivity Detection

R309 is a wireless emergency button alarm device, which can realize the wirelessalarm function together with other devices through the buttons on the device. At
the same time, the device has built-in vibration sensors to further improve thealarm system.

※ R30900 Lanyard Version※ R30901 Wristband Version

Main Characteristics◼ Emergency alarm status detection◼ Inactivity detection◼ IP67

Technical Parameter
Input Power

2 x 3.0V CR2032 button batteries

Operating Voltage

2.5V to 3.0V

Standby Current≤6uA

Battery Accuracy±0.1V

Dimension

R30900: 48mm x 55.5mm x 18.2mm
R30901: 48mm x 55.5mm x 19.8mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~55°C
21

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311A/R313A Wireless Door / Window Sensor
R311A / R313A is equipped with a reed sensor, which
can be used to detect the status of the door andwindow.
※ R311A Built-in antenna※ R313A External antenna

Main Characteristics◼ Door / window status detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

12uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy±0.1V

Main Body Dimensions

R311A: 57mm x 35mm x 15mm
R313A: 57mm x 38.05mm x 15mm

Magnet Dimension

43mm x 13mm x 12mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~55°C

22
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311D/R313D Wireless Asset Sensor
R311D / R313D has a simple positioning function
which can detect the position status of itself. The
device can report RSSI and SNR information to thegateway for processing periodically and locating its
position.
※ R311D Built-in antenna※ R313D External antenna

Main Characteristics◼ RSSI and SNR detection◼ Simple positioning◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

16uA /3.0V

Transmitting Current (max)

120mA / 3.0V

Receiving Current (max)

11mA / 3.0V

Battery Accuracy±0.1V

Dimension

R311D: 57mm x 35mm x 15mm
R313D: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

23
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311DA/R313DA Wireless Vibration Sensor, Rolling Ball Type
R311DA / R313DA can detect vibrations or moving
signals and transmit the detected data to other devices
through the wireless network※ R311DA Built-in antenna※ R313DA External antenna

Main Characteristics◼ Vibration detection◼ Rolling Ball Type
◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Voltage Accuracy±0.1V

Vibration Sensor Sensitivity

In a horizontal position, be easy to trigger
with a shaking

Dimension

R311DA: 57mm x 35mm x 15mm
R313DA: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

24
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311DB/R313DB Wireless Vibration Sensor, Spring Type
R311DB / R313DB can detect vibrations or moving
signals and transmit the detected data to other devices
through the wireless network※ R311DB Built-in antenna※ R313DB External antenna

Main Characteristics◼ Vibration detection◼ Spring Type
◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Voltage Accuracy±0.1V

Vibration Sensor Working
Principle

When it is at rest, it is in the open state OFF
state. When the external force is touched toreach the corresponding vibration force, or
when the moving speed reaches theappropriate centrifugal force, the conductive
pin will instantly reach the ON state.

Dimension

R311DB: 57mm x 35mm x 15mm
R313DB: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C
25

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311W/R313W Wireless 2-Gang Water Leak Detector
When the R311W / R313W detects leaks, it will send amessage to the gateway.
※ R311W Built-in antenna※ R313W External antenna

Main Characteristics◼ Water leaking detection◼ Main body-IP30, Sensor-IP67

Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

12uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy±0.1V

Water Leakage Material

UL2468 28AWG

Water Line Core resistance

1.3 Ω / meter

Water Line Diameter

1mm

Water Line Length

1000mm (±5mm)

Water Line Flame Rating

VW-1

Dimension

R311W: 57mm x 35mm x 15mm
R313W: 57mm x 38.05mm x 15mm

26
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R312/R313M Wireless Door Bell Button
R312 / R313M is a button device which can detect
whether the doorbell is triggered.
※ R312 Built-in antenna※ R313M External antenna※ The pressing time of the alarm button can be

configured through the command.

Main Characteristics◼ Doorbell status detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

14uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy±0.1V

Dimension

R312: 57mm x 35mm x 15mm
R313M: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

27
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R312A/R313MA Wireless Emergency Button
R312A / R313MA is an emergency button device which
can detect whether the button is triggered.
※ R312A Built-in antenna※ R313MA External antenna※ The pressing time of the alarm button can be

configured through the command.

Main Characteristics◼ Button status detection◼ Comes with key ring for easy fixing and carrying◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

13uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy±0.1V

Dimension

R312A: 57mm x 35mm x 15mm
R313MA: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

28
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R315 Series Wireless Multifunction Sensor

R31511

R31512

R31513

R31521

R31522

R31523

R31524

R31527

R31531

R31533

R31535

R31538R31545

R31555

R31559R31560For more R315 series information, please refer to this file:
http://www.netvox.com.tw/download/R315combination.xlsx
29
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R315 Series Wireless Multifunction Sensor

R31561

R31570R31594

R315101

R315102

R31597

For more R315 series information, please refer to this file:
http://www.netvox.com.tw/download/R315combination.xlsx

30
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R315 Series Wireless Multifunction Sensor
R315 series can be connected with temperature and humidity, lighting, door
magnetism, vibration, infrared detection, emergency button, tilt detection, waterleakage detection, seat state detection, dry contact in, and digital output.
Netvox presents to you the latest 8 in 1 combination, a more powerful andmultifunctional option.

Main Characteristics◼ 8 in 1 Multi-Sensor◼ Main body-IP30

Internal Sensor:

External Sensor:

✓
✓
✓
✓
✓
✓

✓
✓
✓
✓
✓
✓
✓

Temperature and humidity sensor
Light sensor
PIR
Internal vibration
Emergency button
Tilt sensor

Water leak sensor
Glass break sensor
External vibration
Reed switch
Seat occupancy sensor
Dry contact in
DO out (3v)

Technical Parameter
Input Power

2x 3V CR2450 button batteries

Operating Voltage

2.3V to 3VPIR Detectable Angle

80 ° horizontally and 90 ° vertically

PIR Detectable Range

2.5m

Vibration Sensor Type

Roll Ball Tilt Switch

Glass Break Sensor Type

Piezoelectric buzzer

Glass Break Sensing Range

within 2.5m radius

External Sensor Wire Length

100 cmSeat Sensor Pressure Range

200-300g

Seat Sensor Dimension

300mm x 300mm x 0.65mm

Main Body Dimension

75.5mm x 44mm x 19.35mm

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

31

R602A/R602B Wireless Siren
R602A / R602B has four kinds of alarm sounds – fire,
emergency, burglar, doorbell and a mute mode. It also
has the high-brightness alarm flasher.
※ R602A: Only DC12V power supply※ R602B: Supports DC and rechargeable battery

power supplies.

Main Characteristics◼ Different types of alarm sounds◼ Different ways of flashing lights◼ Class C device

Technical Parameter

Input Power

R602A

R602B

DC 12VDC 12V &3 sections 1.2V AAA
Ni-MH rechargeable
batteries/

about 24 hours

Backup rechargeable
battery once full use timeWorking Current (max)

250mA(DC 12V)

Standby Current (max)

30mA(DC 12V)

Alarm Sound Level≧80dB

Dimension

Ø 85mm x 52mm

Environment Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

32
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R603 Wireless Customized Voice Announcer
R603 is a wireless siren.
With 10 types of alarm sounds (fire / emergency /burglar alarm),RGB LED light, R603 can be controlled
through AppServer and customized the settings ofalarm sounds and light.
With all these functions, R603 helps you improvesecurity and provides customized options for eachapplication.

Main Characteristics◼
◼
◼
◼

10 Audio to Upload
Programmable RGB LED Color
Adjustable Volume and Mute Mode
2 LED Flash Modes

Technical Parameter
Input PowerDC 12V

Backup rechargeable
battery once full use timeabout 24 hours

Working Current (max)

250mA(DC 12V)

Standby Current (max)

30mA(DC 12V)

Alarm Sound Level≧80dB

Dimension

Ø 85mm x 52mm

Environment Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

33
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718DA/R718DA2
Wireless 1-Gang/2-Gang Vibration Sensor, Rolling Ball Type
R718DA / R718DA2 can detect the vibration or
movement signal, and transmit the detected data toother devices through the wireless network.

※ It is not suitable for the fast-vibrating environment

Main Characteristics◼ Vibration detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Sensor Characteristic

When the vibration sensor is tilted and thetilting angle is greater than 10 degrees, it willbe OFF mode. When the tilt level changes,
and the triggering end is lower than tilt angle
10 degrees, it will be ON state. The modulecandetect open circuit OFF state and closed
circuit ON state signal to detect vibration or
move.

External Cable Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C
34

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718DB/R718DB2 Wireless 1-Gang/2-Gang Vibration Sensor, Spring Type
R718DB / R718DB2 can detect the vibration or
movement signal, and transmit the detected data toother devices through the wireless network.

※ It is not suitable for the fast-vibrating environment

Main Characteristics◼ Vibration detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Sensor Characteristic

When it is at rest, it is in the open state OFF
state. When the external force is touched toreach the corresponding vibration force, or
when the moving speed reaches theappropriate centrifugal force, the conductive
pin will instantly reach the ON state. Whenthe external force disappears, the switch
returns to the OFF state.

External Cable Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

35
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718F/R718F2
Wireless 1-Gang/2-Gang Reed Switch Open/Close Detection Sensor
R718F / R718F2 is equipped with a reed sensor which
can be used to detect the status of the door and thewindow.

Main Characteristics◼ Reed switch status detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Sensor Characteristic

Inside the magnetic range, it is at on state(conducting).
When out of the magnetic range, it is at off
state (non-conducting). Sensing distanceinside magnetic range is 2cm.

External Cable Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

36
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718T/R718T2 Wireless 1-Input/2-Input Push Button Interface
R718T / R718T2 can connect with an external pushbutton and detect whether the external button ispressed.
※ The pressing time of the alarm button can be
configured through the command.

Main Characteristics◼ Push button interface◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Standby Current

22 uA

Wake up Current

6.3mA@3.3V

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Dimension

112mm x 88mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

37
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718TB Wireless Push Button
R718TB is a wireless push button device. When people
encounter danger and need emergency help, press thepush button.
※ The pressing time of the alarm button can be
configured through the command.

Main Characteristics◼ Push button◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Standby Current

30.17 uA

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Dimension

112mm x 65mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

38
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA02A Wireless Smoke Detector
RA02A has a built-in photoelectric smoke detector andbuzzer. It can detect the smoke density in theenvironment and sound alarm when the smoke
density exceeds the default value.

Main Characteristics◼ Smoke detection◼ High temperature detection (>60°C)◼ IP20Technical Parameter
Input Power2 x1.5V AAA alkaline battery

Operating Voltage

2.3V to 3.3V

Standby Current

12uA/3.0v

Working Current While
Alarming

580mA/3.0v

Alarming Decibel

85dBm @3m

Alarming Concentration

0.65~15.5% obs/m

Dimension

Ø 106mm x 40.6mm

Operating Temperature-10°C ~ 55°C

Operating Humidity<90%RH (no condensation)

Storage Temperature-40°C~85°C※ RA02A is an auxiliary smart smoke sensor which must be installed with thefire-fighting smoke sensor.
※ RA02A cannot be used to replace the fire-fighting smoke sensor.

39
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA02C Wireless CO Detector
RA02C is a device for the detection of harmful gases in
the home environment. It is suitable for the detectionof CO (carbon monoxide). When the concentration
exceeds the preset value, it will trigger the alarm.

Main Characteristics◼ Carbon monoxide◼ High temperature detection (>60°C)◼ IP20Technical Parameter
Input Power2 x1.5V AAA alkaline battery

Standby Current

18uA/3.0v

Average Operating Current

70uA/3.0v

Current While Alarming

20mA/3.0v

Alarming Decibel

85dBm@3m

CO Detection Range

0 ~ 1000ppm

Dimension

Ø 106mm x 40.6mm

Operating Temperature-20°C~55°C

Operating Humidity<90%RH (no condensation)

Storage Temperature-40°C~85°C

40
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA02D1 Wireless Liquefied Petroleum Gas Detector
RA02D1 is a liquified petroleum gas detector. It can
detect the LPG concentration in the environment,
and sound alarm when the concentration exceeds thedefault value.
※ Trigger alarm when LPG concentration exceeds

5% LEL, and stop alarm when it falls below 2%.

Main Characteristics◼ Liquified petroleum gas detection◼ High temperature detection (>60°C)◼ IP20Technical Parameter
Input Power

DC12V

Operating Current<150mA

Alarm Decibel Value

85dB (3 meters away)

Liquid Petroleum Gas
Measurement Range

500~10000 ppm

Dimensions

Ø 106mm x 40.6mm

Operating Temperature-20°C~55°C

41
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA02G Wireless Cigarette Smoke, Vaping and Bullying Alarm Sensor
RA02G is a smoking and noise detector with an antitamper alarm. Indoor environments, such as schools,
hospitals, and stations, can be easily monitored by thestable and functional RA02G. As soon as it detects
smoke, excessive noises, or vibration, it will sound thealarm to alert users.

Main Characteristics
◼
◼
◼
◼
◼
◼
◼
◼

Smoking and noise detection
Anti-tamper alarm
Battery backup
Customize audio alerts or muteConnect PoE splitter
Adjust sensitivity / alarm volume
Detect power outage
IP30

Technical Parameter
Input PowerDC12V/1A

Backup Power2 x1.5V AAA alkaline battery

Vibration sensor

Ball-type omnidirectional signal trigger switch

Smoke Detector
Comprehensive Response Time

≤10 seconds

Sound Sensitivity-36±3db

Sound Frequency

20~10000 Hz

Dimensions

Ø 106mm x 40.6 mm

Length of adapter cable

1.5m

Ambient Humidity Range<90%RH (no condensation)

Ambient Temperature Range-20°C~55°C

42
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RB11E Wireless Occupancy / Light / Temperature Sensor
RB11E combines infrared detection, temperature, andillumination sensors. During infrared real-time
detection, if a people or other organism which is activein the monitoring area, RB11E will detect the infrared
signal .

Main Characteristics◼ Occupancy, temperature, illuminance and disassembled detection◼ IP30Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Mounting Height

2 to 2.2 meters above ground level

Mounting Angle

Tilt 15° downward

Sensing Angle

Horizontal 110°, vertical 60°

Sensing Distance

2m to 12m

Temperature Accuracy±2°C

Light Sensor Measurement
Range

2~1100 LUXLight Sensor Accuracy≦15%

Dimension

78mm x 78.8mm x 82.2mm

Weight125.8gOperating Temperature-20°C ~55°C

Storage Temperature-40°C~85°C

43
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311B/R313B Wireless Light Sensor
When the illuminance exceeds the set threshold, areport will be sent immediately.
※ R311B Built-in antenna※ R313B External antenna

Main Characteristics◼ Illuminance detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

12uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Detecting Illumination Range

1~3000 lux

Dimension

R311B: 57mm x 35mm x 15mm
R313B: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

44
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311CA/R313CA Wireless 2-Input Dry Contact Interface
R311CA is externally connected to two dry contacts forcustomers to connect to the equipment under test,
such as switches, buttons, sensors, relays, reedswitches, etc. At the same time, wireless alarm andother functions can be realized through the built-in
wireless module.
※ R311CA Built-in antenna※ R313CA External antenna

Main Characteristics◼ Dry contact Interface◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

10uA /3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Wire Material

UL2468 28AWG

Wire Length

1000mm (±5mm)

Wire Flame Resistance Rating

VW-1

Main Body Dimension

R311CA: 57mm x 35mm x 15mm
R313CA: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

45
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311CB/R313CB Wireless Window Sensor with Glass Break Detector
R311CB / R313CB device has a built-in reed switch
sensor and can be externally connected to the reedswitch. It can be used for door and window switch
status detection and externally connected to broken
glass sensor to detect the glass status.
※ R311CB Built-in antenna※ R313CB External antenna

Main Characteristics◼ Reed switch and glass break detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Sensor Characteristic

Within the magnetic range, it is at off state(conducting). When out of the magnetic
range, it is at on state (non-conducting).

Main Body Dimension

R311CB: 57mm x 35mm x 15mm
R313CB: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

46
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311CC/R313CC Wireless 2-Gang Door/Window Sensor
R311CC / R313CC is equipped with two external reedswitches, which can be used for door and window
switch state detection.
※ R311CC Built-in antenna※ R313CC External antenna

Main Characteristics◼ Reed switch detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

10uA /3.0V

Transmitting Current (max)

120mA / 3.0V

Receiving Current (max)

11mA / 3.0V

Battery Accuracy±0.1V

Sensor Case Size

42mm x 13mm x 12mm

External Cable Length

1 meter

Main Body Dimension

R311CC: 57mm x 35mm x 15mm
R313CC: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

47
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311G/R313G Wireless Light Sensor
R311G / R311G has the built-in light sensor. It can beused for detecting ambient light intensity and can send
the ambient illumination value.
※ R311G Built-in antenna※ R313G External antenna

Main Characteristics◼ Illuminance detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

12uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Detecting Illumination Range

1~3000 lux

Dimension

R311G: 57mm x 35mm x 15mm
R313G: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

48
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311K/R313K Wireless Tilt Sensor
When the R311K / R313K has a tilt of 45 degrees ormore in any direction, a tilt signal will be issued.
※ R311K Built-in antenna※ R313K External antenna※ It needs to be installed vertically.

Main Characteristics◼ Tilt detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

10uA / 3.0V

Transmitting Current (max)

120mA / 3.0V

Receiving Current (max)

11mA/ 3.0V

Battery Accuracy± 0.1V

Conversion Angle

45±5 degrees

Contact ResistanceLess than 10 ohms

Insulation ResistanceMore than 100 megohms

Installation Type

Suitable for PCB at vertical state

Dimension

R311K: 57mm x 35mm x 15mm
R313K: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C
49

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311LA/R313LA Wireless Infrared Proximity Sensor
R311LA / R313LA is able to detect the existence of an
object nearby. It has an infrared proximity sensor thatcan detect if there is an object existing within its
detection range.
※ R311LA Built-in antenna※ R313LA External antenna

Main Characteristics◼ Infrared proximity detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

12uA / 3.0V

Transmitting Current (max)

120mA / 3.0V

Receiving Current (max)

11mA/ 3.0V

Battery Accuracy± 0.1VSensing DistanceApproximately 5cm

Dimension

R311LA: 57mm x 35mm x 15mm
R313LA: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

50
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311WA/R313WA Wireless 2-Gang Seat Occupancy Sensor
R311WA / R313WA is a device that detects thepresence of a seat. If there is someone on the seat,
R311WA / R313WA will send a message to the gateway.
When detecting no one on a sensor seat, it will send anormal status message back to the gateway.
※ R311WA Built-in antenna※ R313WA External antenna

Main Characteristics◼ Seat occupancy detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Pressure Range

200-300g

Wire Material

UL2468 28AWG

Wire Length

1000mm (±15mm)
R311WA: 57mm x 35mm x 15mm
R313WA: 57mm x 38.05mm x 15mm

Main Unit Casing Size

Cushion Film Sensor Size

300 mm x 300 mm x 0.65 mm

Operating Temperature-20°C~55 °C

Operating Humidity<90 %RH (no condense)

Storage Temperature-40°C~85 °C

51
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R711 Wireless Temperature and Humidity Sensor
R711 is mainly used to measure the indoor ambient
temperature and humidity.
※ Temperature Measurement Range: -20°C~55°C※ Humidity Measurement Range: 0%RH~100%RH

Main Characteristics◼ Temperature and humidity detection◼ IP40Technical Parameter
Input Power2 x 1.5V AA alkaline battery

Operating Voltage

2.3V to 3.0V

Standby Current

12uA/3V

Transmitting Current (max)

120mA/3V

Receiving Current (max)

11mA/3V

Battery Accuracy±0.1V

Temperature Range-20°C~55°C

Temperature Accuracy±0.8°C @25°C (indoor)

Humidity Range

0%RH~100%RH

Humidity Accuracy±5%RH @25°C

Dimension

108.5mm x 34.2mm x 19mm

Operating Humidity<90%RH

Operating Temperature-20°C ~55°C

Storage Temperature-40°C~85°C
52

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R712 Wireless Outdoor Temperature and Humidity Sensor
R712 is mainly used to detect the temperature andhumidity in outdoor air, and also carrying awaterproof housing.
※ Temperature Measurement Range: -20°C~55°C※ Humidity Measurement Range: 0%RH~100%RH

Main Characteristics◼ Temperature and humidity detection◼ IP54

Technical Parameter
Input Power2 x 1.5V AA alkaline battery

Operating Voltage

2.3V to 3.0V

Standby Current

12uA/3V

Transmitting Current (max)

120mA/3V

Receiving Current (max)

11mA/3V

Battery Accuracy±0.1V

Temperature Range-20°C~55°C

Temperature Accuracy±1.5°C @25°C

Humidity Range

0%RH ~ 100%RH

Humidity Accuracy±10%RH @25°C

Dimension

112mm x 34mm x 17mm

Waterproof Housing Dimension

222mm x 130mm x 195mm

Operating Humidity<90%RH

Operating Temperature-20°C~55°C

Storage Temperature-40°C~85°C
53

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718A/R718A01
Wireless Temperature and Humidity Sensor For Low Temperature Environment
R718A / R718A01 can be used in general refrigeratorsor domestic logistics refrigerators that store andtransport food, medicines, flowers and otherperishable goods.
※ R718A01: Capable to cache 50 records oftemperature and humidity data.

※ Temperature Measurement Range: -40°C~55°C

Main Characteristics※ Humidity Measurement Range: 0%RH~100%RH◼ Temperature and humidity detection◼ IP65

Technical Parameter
Data Storage Function

R718A

R718A01

XO

Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Battery Accuracy±0.1V

Temperature Detecting Range-40°C~55°C

Temperature Accuracy±0.5°C @25°C

Humidity Detecting Range

0%RH~100%RH

Humidity Accuracy±3%RH @25°C

Dimension

112mm x 65mm x 28mm

Operating Temperature-40°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

54
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718AB Wireless Temperature and Humidity Sensor
R718AB can detect the temperature and humidity of
the air.
※ Temperature Measurement Range: -20°C~55°C※ Humidity Measurement Range: 0%RH~100%RH

Main Characteristics◼ Temperature and humidity detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Battery Accuracy±0.1V

Temperature Range-20°C~55°C

Temperature Accuracy±1°C @25°C

Humidity Range

0%RH~100%RH

Humidity Accuracy±4%RH @25°C

Dimension

112mm x 65mm x 28mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

55
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718AD Wireless Temperature Sensor
R718AD is mainly used to measure the temperature ofobject.
※ Temperature Measurement Range: -40°C~125°C※ Digital Thermometer

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Battery Accuracy±0.1V

Temperature Detecting Range-40°C~125°C

Temperature Accuracy±1°C

Cable Length1m

Probe Size Length

50mm, outer diameter: 5mm

Probe Material

Stainless steel 316

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C
56

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718BC /R718BC Wireless Temperature Sensor - PT1000 Clamp Probe
R718BC / R718BC2 is a wireless temperature sensor
with a clamp probe, allowing users to securely attach it
to a surface and easily measure the temperature of atube.
※ Temperature Measurement Range: -50°C~150°C※ PT1000※ Clamp probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-50°C ~ 150°C

Accuracy± 3℃

Lead Length2m

Adjustable Range

Diameter: 21 – 38mm

57
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718BP / R718BP2 Wireless Temperature Sensor - PT1000 Patch Probe
R718BP / R718BP2 is a wireless temperature sensor
with a patch probe, allowing users to attach it to thesurface and easily measure the temperature of an
object.
※ Temperature Measurement Range: -50°C~150°C※ PT1000※ Patch probe

Main Characteristics◼ Temperature detection◼ Main body-IP65, Sensor-IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-50°C ~ 150°C

Accuracy± 2℃

Lead Length

2m

Patch Probe Dimension

20mm x 25mm

58
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B120/R718B220 Wireless 1-Gang/2-Gang Temperature Sensor
R718B120 / R718B220 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -70°C~200°C※ PT1000※ Round head probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-70°C ~ 200°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±0.8°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -70°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 200°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.6}°C
Lead Length2m

Probe Specifications

5mm in diameter x 30mm in length, roundhead probe
59

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B121/R718B221 Wireless 1-Gang/2-Gang Temperature Sensor
R718B121 / R718B221 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -70°C~200°C※ PT1000※ Needle probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-70°C ~ 200°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±0.8°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -70°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 200°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.6}°C
Lead Length
Probe Specifications

2m
5mm in diameter x 150mm in length, needle
probe
60

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B122/R718B222 Wireless 1-Gang/2-Gang Temperature Sensor
R718B122 / R718B222 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -50°C~180°C※ PT1000※ Absorption probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-50°C ~ 180°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±1°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -50°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1.5}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 180°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.8}°C
Lead Length2m

Probe Specifications

5mm in diameter, absorption probe, NdFeB
magnet61

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B140/R718B240 Wireless 1-Gang/2-Gang Temperature Sensor
R718B140 / R718B240 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -40°C~375°C※ PT1000※ Round head probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP50

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40°C ~ 375°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±0.8°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 375°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.6}°C
Lead Length2m

Probe Specifications

5mm in diameter x 30mm in length, roundhead probe
62

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B141/R718B241 Wireless 1-Gang/2-Gang Temperature Sensor
R718B141 / R718B241 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -40°C~375°C※ PT1000※ Needle probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP50

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40°C ~ 375°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±0.8°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 375°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.6}°C
Lead Length
Probe Specifications

2m
5mm in diameter x 150mm in length, needle
probe
63

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B150/R718B250 Wireless 1-Gang/2-Gang Temperature Sensor
R718B150 / R718B250 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -40°C~500°C※ PT1000※ Round head probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP50

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40°C~500°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±0.8°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 500°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.6}°C
Lead Length2m

Probe Specifications

5mm in diameter x 30mm in length, roundhead probe
64

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718B151/R718B251 Wireless 1-Gang/2-Gang Temperature Sensor
R718B151 / R718B251 connects an external resistancetemperature detector to measure the temperature.
※ Temperature Measurement Range: -40°C~500°C※ PT1000※ Needle probe

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP50

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40°C~500°C

Measurement Accuracy(1)The host body and sensor are in the same
temperature range:
0°C ≤ t ≤ 55°C, Accuracy: ±0.8°C(2)The host body and sensor are in the
different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2 < 0°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+1}°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C <T2 ≤ 500°C (Sensor)
Accuracy: ±{(0.15 + 0.002x |T2|)+0.6}°C
Lead Length
Probe Specifications

2m
5mm in diameter x 150mm in length, needle
probe
65

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718CK/R718CK2 Wireless 1-Gang/2-Gang Thermocouple Sensor - Type K
R718CK / R718CK2 is used to detect temperature of
the object and medium which thermocouple iscontacted.

※ Temperature Measurement Range: -40°C~375°C※ Thermocouple Sensor - Type K

Main Characteristics◼ Temperature detection◼ IP50Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40°C~375°C

Measurement Accuracy(1)The host body and K-type thermocouple
are in the same temperature range:
Temperature Range: 0°C ≤ t ≤ 55°C,
Accuracy: ±1.5°C(2)The host body and K-type thermocouple
are in different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2 < 0°C (Sensor)
Accuracy: ±2°C
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C < T2 ≤ 375°C (Sensor)
Accuracy: ±2°C

Lead Length

1m
66

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718CKAB Wireless Temperature and Humidity Sensor with Thermocouple
Sensor - Type K
R718CKAB connects a temperature/humidity sensor
and K-Type thermocouple, which respectively detects
temperature and humidity, and the surface
temperature of an object.

Main Characteristics◼ Temperature / Humidity / Thermocouple detection◼ IP50Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-20°C~55°C

Humidity Range

0%~100%

Thermocouple Range-40°C~375°C

Measurement Accuracy(1)The host body and K-type thermocouple
are in the same temperature range:
Temperature Range: 0°C ≤ t ≤ 55°C,
Accuracy: ±1.5°C(2)The host body and K-type thermocouple
are in different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2 < 0°C (Sensor)
Accuracy: ±2°C
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C < T2 ≤ 375°C (Sensor)
Accuracy: ±2°C

Lead Length

1m
67

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718CN/R718CN2
Wireless 1-Gang/2-Gang Thermocouple Sensor - Type N
R718CN / R718CN2 is used to detect temperature of
the object and medium which thermocouple iscontacted.

※ Temperature Measurement Range: -40°C~800°C※ Thermocouple Sensor - Type N

Main Characteristics◼ Temperature detection◼ IP50Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40~800°C

Measurement Accuracy±2°C (-40~375°C)±0.004t+1°C (375°C~800°C)

Lead Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

68
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718CT/R718CT2 Wireless 1-Gang/2-Gang Thermocouple Sensor - Type T
R718CT / R718CT2 is used to detect temperature of
the object and medium which thermocouple iscontacted.

※ Temperature Measurement Range: -40°C~125°C※ Thermocouple Sensor - Type T

Main Characteristics◼ Temperature detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-40 °C ~ 125°C

Measurement Accuracy(1)The host body and T-type thermocouple
are in the same temperature range:
Temperature Range: 0°C ≤ t ≤ 55°C,
Accuracy:±0.8°C(2)The host body and T-type thermocouple
are in different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2< 0°C (Sensor)
Accuracy: ±2°C

T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C < T2 ≤ 125°C (Sensor)
Accuracy: ±1.5°C
Lead Length

1m
69

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718CTAB Wireless Temperature and Humidity Sensor with Thermocouple
Sensor - Type T
R718CTAB connects a temperature/humidity sensor
and T-Type thermocouple, which respectively detects
temperature and humidity, and the surface
temperature of an object.

Main Characteristics◼ Temperature / Humidity / Thermocouple detection◼ Main body-IP65/IP67, Thermocouple-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Range-20°C~55°C

Humidity Range

0%~100%

Thermocouple Range-40 °C ~ 125°C

Measurement Accuracy(1)The host body and T-type thermocouple
are in the same temperature range:
Temperature Range: 0°C ≤ t ≤ 55°C,
Accuracy:±0.8°C(2)The host body and T-type thermocouple
are in different temperature ranges:
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: -40°C ≤ T2< 0°C (Sensor)
Accuracy: ±2°C
T1: 0°C ≤ T1 ≤ 55°C (Host body)
T2: 55°C < T2 ≤ 125°C (Sensor)
Accuracy: ±1.5°C

Lead Length

1m
70

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA1 Wireless CO Sensor
R718PA1 is a wireless communication device fordetecting the concentration of CO in the air.

Main Characteristics◼ Carbon monoxide detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

CO Measurement Range

0 to 2000ppm

CO Measurement Method

Electrochemical sensors

CO Measurement Accuracy<± reading 3% (@25°C)

Response Time

≤50s

Working Pressure Range

Standard atmospheric pressure ±10%

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

71
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA2 Wireless NO Sensor
R718PA2 is a wireless communication device fordetecting the concentration of NO in the air.

Main Characteristics◼ Nitric oxide detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

NO Measurement Range

0 to 2000ppm

NO Measurement Method

Electrochemical sensors

NO Measurement Accuracy<± reading 2% (@25°C)

NO Measurement Resolution< 1ppmResponse time

< 60s

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

72
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA3 Wireless O3 Sensor
R718PA3 is a wireless communication device fordetecting the concentration of O3 in the air.

Main Characteristics◼ Ozone detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

O3 Measurement Range

0 to 20ppm

O3 Measurement Method

Electrochemical sensors

O3 Measurement Accuracy<± reading 3% (@25°C)

Response time

< 15s

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

73
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA4 Wireless H2S Sensor
R718PA4 is a wireless communication device fordetecting the concentration of H2S in the air.

Main Characteristics◼ Hydrogen sulfide detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

Working Current

60mA (With external sensor)

H2S Measurement Range

0 to 100 ppm

H2S Measurement Method

Electrochemical sensors

H2S Measurement Accuracy<± reading 2% (@25°C)

H2S Measurement Resolution< 0.1ppm

Response time

≤ 30s

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

74
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA5 Wireless NO2 Sensor
R718PA5 is a wireless communication device fordetecting the concentration of NO2 in the air.

Main Characteristics◼ Nitrogen dioxide detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

NO2 Measurement Range

0 to 20 ppm

NO2 Measurement Method

Electrochemical sensors

NO2 Measurement Accuracy±0.6 ppm

Response Time

≤ 15s

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

75
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA6 Wireless SO2 Sensor
R718PA6 is a wireless communication device fordetecting the concentration of SO2 in the air.

Main Characteristics◼ Sulphur dioxide detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

SO2 Measurement Range

0 to 20 ppm

SO2 Measurement Method

Electrochemical sensors

SO2 Measurement Accuracy<± reading 3% (@25°C)

Response Time

≤ 15s

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

76
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA7 Wireless Noise Sensor
R718PA7 is a wireless communication device fordetecting the noise decibel value.

Main Characteristics◼ Noise detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input PowerDC 12V power supply

Noise Measurement Range

30dB to 130dB

Noise Measurement Accuracy

0.1dB

Noise Measurement Error± 3dB

Response Time

≤ 3s

Frequency Response

20Hz –12.5Khz

Weighting Curve

A-Weighting

Dimensions

Main body: 112 mm x 88.19mm x 32 mm
Noise Sensor: 147mm x 115mm x 41mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

77
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA8 Wireless PH Sensor
R718PA8 is a wireless communication device fordetecting PH value.

Main Characteristics◼ PH value detection◼ Main body-IP65/IP67, Sensor-IP68

Technical Parameter
Input PowerDC 12V power supply

PH Measurement Range

0 to 14 PH

PH Measurement Resolution

0.01 PH

Wire Length

5m (Other lengths customizable)

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

78
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA10 Wireless Turbidity Sensor
R718PA10 is a wireless communication device fordetecting turbidity value and temperature of thesolution.

Main Characteristics◼ Turbidity detection◼ Main body-IP65/IP67, Sensor-IP68

Technical Parameter
Input PowerDC 12V power supply

Turbidity Range

0.1 to 1000 ntu

Turbidity Resolution

0.1 ntu

Turbidity Accuracy<5% or 0.3 ntu

Maximum Depth

Underwater 10 m

Wire Length

10m (Other lengths customizable)

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

79
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA11 Wireless Liquid Level Sensor
R718PA11 is a wireless communication device fordetecting the depth of liquid in the container.
※ Others line length/range can be customized.

Main Characteristics◼ Liquid level detection◼ Main body-IP65/IP67, Sensor-IP68

Technical Parameter
Input PowerDC 12V power supply

Measurement Range

10m (Other range customizable)

Line Length

12m (Other lengths customizable)

Accuracy

0.25%FS (Typical)

Dimension

112mm x 88mm x 32mm

WeightAbout 160g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

80
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PA22 Wireless Bottom-Mounted Ultrasonic Liquid Level Sensor
R718PA22 can be mounted at the bottom of the tankwithout breaking or making holes.
It can detect pure liquids, such as clear water, oil,diesel, gasoline and liquefied gas in small, medium orlarge capacity tanks.

Main Characteristics◼ Bottom-Mounted Ultrasonic Liquid Level detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input PowerDC 12V power supply

Measuring Range

80~2200mm ( 0-80mm is blind zone)

Measurement Accuracy± (5+S*0.5%)mm(“S” represents the current liquid level height)

Resolution

1mm

Measurable Container Thickness 4~7mm
Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

81
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PB15 / R718PB15A
Wireless Soil Moisture / Temperature / Electrical Conductivity Sensor
R718PB15 / R718PB15A is a wireless communication
device for detecting soil temperature, moisture
content and soil electrical conductivity.
※ R718PB15A with a waterproof housing.

Main Characteristics
◼
◼
◼
◼
◼

Soil temperature detection
Moisture content detection
Soil electrical conductivity detection
R718PB15: Main body-IP65/IP67,Sensor:IP67
R718PB15A: Main body-IP67,Sensor:IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Battery Accuracy±0.1V

Soil Temperature Range-40°C to 80°C

Soil Moisture Content Range

0 to 100%

Soil EC Range

0 to 20000 us/cm

Sensor Cable Length2mDimension

R718PB15: 112mm x 88mm x 32mm
R718PB15A: Ø 80mm x 134mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

82
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PE Top-Mounted Ultrasonic Level Sensor
The propagation medium of the R718PE ultrasonicsensor is air, so the measured object can be any liquid
or solid object with an even surface.

Main Characteristics◼ Top-Mounted Ultrasonic Level detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Measuring Range

0.25-8m

Blind Zone

0-0.25m

Detection Angle

About 15°

Measurement Accuracy±(1+Sx0.3%) cm, S refers to the detecteddistance between thedevice and the detected object.

Cable Length

About 40cm

Dimension

112mm x 88mm x 32mm

Operating Temperature-15°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-25°C~70°C

83
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PE02 / R718PE02D Wireless Lidar Material Level Detection Sensor
R718PE02 / R718PE02D uses LiDAR radar for singlepoint ranging for the material level detection industry.
Based on the ToF (Time of Flight) schematic, it provides
stable, accurate, and reliable ranging performance by
optimizing the optical system and built-in algorithms.
※R718PE02: Battery power supply※R718PE02D: DC12V power supply

Main Characteristics◼ Lidar Material Level detection◼ R718PE02: Main body-IP65/IP67, Sensor-IP5X◼ R718PE02D: Main body-IP30, Sensor-IP5X

Technical Parameter
R718PE02
Input Power

Measuring Range

R718PE02D

8 x 3.6V ER14505
lithium batteries
90% Reflectivity, 0K lux
10% Reflectivity, 0K lux
90% Reflectivity, 100K lux
10% Reflectivity, 100K lux

DC5V/2A
0.1m to 25m
0.1m to 12m
0.1m to 25m
0.1m to 12m

Blind Zone

0-0.1mDetection Angle

3°

Measurement Accuracy±6 cm (0.1-6m); ±1% (6-25m)

Dimension

Main body: 112mm x 88mm x 32mm
Battery box: 117mm x 89.05 x 82mm
Sensor: 85mm x 59mm x43mm

Operating Temperature-15°C~55°C

Operating Humidity<60% RH (No condensation)

Storage Temperature-25°C~70°C

84
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PG Wireless Light Sensor
R718PG has the built-in light sensor. It can be used for
detecting ambient light intensity and can send theambient illumination value.

Main Characteristics◼ Illuminance detection◼ IP65/IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Illuminance Range

0.01 Lux - 157K Lux

Illuminance Accuracy±20% (In the sunlight)±10% (Test Condition: white LED light, 6500K,
room temperature)

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

85
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PQ Wireless Short-Range Occupancy Sensor
R718PQ has a built-in PIR sensor. If the movement ofpeople or animal is detected within the monitoredarea, the device will report the detected status to
gateway.

Main Characteristics◼ Occupancy detection◼ IP65/IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Wake up Current

6.3mA@3.3V

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Measuring Distance

3.8M (from the main unit)

Detecting Angle

About 72°
(2 meters away perpendicular to the sensor)

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

86
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PQA Wireless Toilet Occupancy Sensor
R718PQA has a reed switch sensor and a built-in PIR
sensor which detects if someone enter the toilet andclose the door, it will report occupancy status.

Main Characteristics◼ Occupancy and reed switch detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Wake up Current

6.3mA@3.3V

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Measuring Distance

3.8M (from the main unit)

Detecting Angle

About 72°
(2 meters away perpendicular to the sensor)

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

87
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718UBB Series
Wireless CO2/Temperature/Humidity/Vibration/Air Pressure/Light Sensor
R718UBB series is a wireless communication device
that can detect CO2 in the environment and can be
combined with a variety of sensors.
※See model combination for optional combination

Main Characteristics◼ CO2, Temperature and humidity sensor, Vibration, Air Pressure, Light sensor◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Temperature Range

400 to 5000 ppm(extended range up to 10000ppm)± (50ppm ± 3% of reading)
Extended range: ± 10% of reading
0°C to 50°

Humidity Range

0%RH to 100%RH

Vibration Type

Roll Ball Tilt Switch

Air Pressure Range

300hPa to 1100hPa

Illuminance Range

0.01 LUX to 157K LUX

CO2 Range
CO2 Accuracy

88
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718UBB Series
Wireless CO2/Temperature/Humidity/Vibration/Air Pressure/Light Sensor

Model Combination
Model

CO2

R718UBB
R718UBB1
R718UBB12
R718UBB123
R718UBB23
R718UBB25
R718UBB125
R718UBB235
R718UBB1235

V
V
V
V
V
V
V
V
V

TH
(1)
V
V
V

V
V

Vibration
(2)

V
V
V
V
V
V
V

Air Pressure
(3)

Light
(5)

V
V

V
V

V
V
V
V

89
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718UBD Series Wireless CO2 / Temperature / Humidity / Vibration / Air
Pressure / Light / PM2.5 / PM10
R718UBD series is a wireless communication device
that can detect CO2 in the environment and can be
combined with a variety of sensors. And transmits thedetected data to other devices through the wirelessnetwork for display, which adopts the SX1276 wirelesscommunication module.
※See model combination for optional combination

Main Characteristics◼ CO2 Temperature and humidity sensor, Vibration, Air Pressure, Light Sensor◼ PM2.5/PM10, TVOC
◼ Main body-IP65, PM2.5/PM10 Sensor-IP67, TVOC Sensor-IP65

Technical Parameter
Input PowerDC 12V

Temperature Range

400 to 5000 ppm
extended range up to 10000ppm± (50ppm ± 3% of reading)
Extended range: ± 10% of reading
0°C to 50°C

Humidity Range

0%RH to 100%RH

Vibration Type

Roll Ball Tilt Switch

Air Pressure Range

300hPa to 1100hPa

Illuminance Range

0.01 LUX to 157K LUX

PM2.5/PM10 Range

PM2.5: 0 to 999ug/m³
PM10: 0 to 1500ug/m³

TVOC Range

0 to 60000ppb

CO2 Range
CO2 Accuracy

90
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718UBD Series Wireless CO2 / Temperature / Humidity / Vibration / Air
Pressure / Light / PM2.5 / PM10

Model Combination
Built-in sensor
Model
CO2
R718UBD
R718UBD1
R718UBD12
R718UBD123
R718UBD23
R718UBD25
R718UBD125
R718UBD235
R718UBD1235
R718UBD126
R718UBD1236
R718UBD1256
R718UBD12356
R718UBD127
R718UBD1237
R718UBD12357
R718UBD1257
R718UBD256
R718UBD257
R718UBD236
R718UBD237
R718UBD2356
R718UBD2357

V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V

TH
(1)
V
V
V

V
V
V
V
V
V
V
V
V
V

External Sensor

Vibration AirPressure
(2)
(3)

V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V
V

Light
(5)

TVOC
(6)

PM2.5/10

(7)

V
V

V
V

V
V
V
V

V
V
V
V

V
V
V
V

V
V

V
V
V
V

V
V
V
V
V
V
V
V
V

V
V
V

V
V

V
V

91
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718VA Wireless Capacitive Proximity Sensor
R718VA is connected to a non-contact capacitive
sensor, which can be installed on the exterior of thecontainer. Without direct contact, the sensor can
detect the current level of water or liquid hand soap
within the measurement range.
※Suitable for installation in flat non-metal containers

Main Characteristics◼ The presence or absence of liquid/object detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Sensing Container Thickness≤20mm (Non-metal:glass, plastic etc.)

Sensitivity

The sensitivity of the non-contact capacitive
sensor must be adjusted in the fieldaccording to different liquids or objects andthe thickness of non-metallic containers.

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

92
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718VB Wireless Capacitive Proximity Sensor
R718VB is to detect the level of toilet tank water, liquid
hand soap, and liquid level of non-metallic pipes (pipeoutside diameter: D ≥11MM). This device is connected
to a non-contact capacitive sensor, which can beinstalled on the exterior of the container. Without
direct contact, the sensor can detect the current
level of water or liquid hand soap within themeasurement range.
※ Suitable for installation in uneven non-metal
containers

Main Characteristics◼ The presence or absence of liquid/object detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Sensing Container Thickness≤20mm (Non-metal:glass, plastic etc.)

Applicable Pipe Diameter Range ≥11mm

Sensitivity

The sensitivity of the non-contact capacitive
sensor must be adjusted in the fieldaccording to different liquids or objects andthe thickness of non-metallic containers.

Dimension

112mm x 88mm x 32mm

WeightAbout 150g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

93
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718WA/R718WA2 Wireless 1/2-Gang Water Leak Detector
If the R718WA / R718WA2 detects a leak, it will sendan alarm message to the gateway.
When the water sensor detects that there is no waterleak again, it will send a normal state message back to
the gateway.

Main Characteristics◼ Water leak detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Wire Material

UL2547 24AWG

Wire Length

1000mm (±5mm)

Wire Flame Resistance Rating

VW-1

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

94
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718WAA
Wireless Water Leak Detector with Temperature and Humidity Sensor
R718WAA can detect the temperature and humidity
value of the current environment and send thetemperature and humidity value information to thegateway for processing.

Main Characteristics◼ Water leak detection◼ Temperature and humidity detection◼ Main body-IP65, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Measurement
Range-20°C to 55°C

Humidity Measurement Range

0%RH to 100%RH

Wire Material

UL2547 28AWG

Wire Length

1000mm (±5mm)

Wire Flame Resistance Rating

VW-1

Dimension

112mm x 93.4mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

95
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718WB/R718WB2
Wireless 1/2-Gang Water Leak Detector with Rope Sensor
R718WB /R718WB2 can detect the leak status throughan external dual-core non-positioning water rope
sensor, and send the detected data to data center
through the wireless network.

Main Characteristics◼ Non-positioning water leak detection◼ Main body-IP65/IP67, Sensor-IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Leakage Rope Material

Conductive Polyethylene + Alloy Wire

Length3000mm (±5mm)

Breaking Strength

60 kg

Detect Core ResistanceLess than 5 ohms/100 meters

Dimension

112mm x 88mm x 32mm

WeightAbout 141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

96
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718WBA Wireless Water Leak Detector (Rope Sensor) with Temperatureand Humidity Sensor
R718WBA can detect the leaking status through anexternal dual-core non-positioning water rope sensor.
It also can detect temperature and humidity.

Main Characteristics◼ Non-positioning water leak detection◼ Temperature and humidity detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Measurement
Range-20°C to 55°C

Humidity Measurement Range

0%RH to 100%RH

Leakage Rope Material

Conductive Polyethylene + Alloy Wire

Length3000mm (±5mm)

Breaking Strength

60 kg

Detect Core ResistanceLess than 5 ohms/100 meters

Dimension

112mm x 88mm x 32mm

WeightAbout 141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C
97

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718X Wireless Ultrasonic Distance Sensor and Temperature Sensor
R718X has a built-in ultrasonic ranging sensor that can
detect the distance from the sensor to the detected
object.

R718X also has the temperature detection function, it
can detect the temperature of the waste bin.

Main Characteristics◼ Ultrasonic distance detection◼ Temperature detection◼ IP66

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Distance of Detection

0.20~3.5m

Distance Accuracy

S±0.12m (The test object is cardboard)

Distance Blind Zone

0~0.20m

Temperature Range-40°C to 55°C

Temperature Accuracy±3°C

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

98
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718Y Wireless Differential Pressure and Temperature Sensor
R718Y is a wireless communication device fordetecting the pressure difference and temperature.

Main Characteristics◼ Differential pressure detection◼ IP40Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Differential Pressure Range-500 Pa to 500 Pa

Differential Pressure Accuracy

3% of reading ± 0.1 Pa

Allowable Overpressure

100 kPa

Rated Burst Pressure

500 kPa

Temperature Accuracy± 3°C (-20°C to 50°C)

Media Compatibility

Air, Nitrogen, Oxygen, Non-condensing

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C ~ 50°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

99
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R719A Wireless Surface-Mounted Parking Sensor
R719A can be used to detect the presence or absenceof parking vehicles in the parking space.

Main Characteristics◼ Parking space detection◼ IP67

Technical Parameter
Input Power

2 x 3.6V ER18505 lithium batteries

Receiving Current (max)

11mA @3.3V

Transmitting Current (max)

120mA/3.3V

Geomagnetic SensorMagnetic Field Detection
Range± 50 gauss

Radar Sensor - Working
Frequency

60GHZ

Radar Sensor - Detection Range

6cm~2mOperating Humidity< 90% RH (No condensation)

Operating Temperature-20°C~75°C

Dimension

150mm x 150mm x 30mm

100
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720A
Wireless Temperature and Humidity Sensor For Low Temperature Environment
R720A can be used in general refrigerators or domestic
logistics refrigerators that store and transport food,medicines, flowers and other perishable goods.
※ Temperature Measurement Range: -40°C~55°C※ Humidity Measurement Range: 0%RH~100%RH

Main Characteristics◼ Temperature and humidity detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Detecting Range-40°C~55°C

Temperature Accuracy±0.5°C @25°C

Humidity Detecting Range

0%RH~100%RH

Humidity Accuracy±4%RH @25°C

Dimension

88mm x 65mm x 19mm

Operating Temperature-40°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

101
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720B
Wireless Temperature and Humidity Sensor with Activity Detection Sensor
R720B can detect the temperature, humidity andmove alarm.
※ Temperature Measurement Range: -40°C~55°C※ Humidity Measurement Range: 0%RH~100%RH

Main Characteristics◼ Temperature, humidity and move alarm detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Detecting Range-40°C~55°C

Temperature Accuracy±0.5°C @25°C

Humidity Detecting Range

0%RH~100%RH

Humidity Accuracy±4%RH @25°C

Dimension

88mm x 65mm x 19mm

Operating Temperature-40°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

102
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720C Wireless Air Pressure and Temperature Sensor
R720C is a wireless communication device fordetecting ambient air pressure and temperature.
※ Temperature Measurement Range: -40°C~55°C

Main Characteristics◼ Air pressure and temperature detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Temperature Detecting Range-40°C~55°C

Temperature Accuracy±1°C @25°C

Air Pressure Range

300-1100hPa

Air Pressure Accuracy±1.5 hPa (950 ... 1050 hPa, 0 ... +40 °C)

Dimension

88mm x 65mm x 19mm

Operating Temperature-40°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

103
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720E Wireless TVOC / Temperature / Humidity Sensor
R720E can detect the temperature, humidity and

TVOC.
※ Temperature Measurement Range: -20°C~55°C※ Humidity Measurement Range: 0%RH~100%RH

Main Characteristics◼ Temperature, humidity and TVOC detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

TVOC Detecting Range

0 ppb - 60000 ppb
0ppb-2008ppb : 1ppb

TVOC Detecting Resolution

2008ppb-11110ppb : 6ppb
11110ppb-60000ppb : 32ppb

TVOC Concentration Range
Reference Description

Excellent: 0-65 ppb
Good: 65-220 ppb
Moderate: 220-660 ppb
Poor: 660-2200 ppb
Unhealthy: 2200-60000 ppb

Temperature Range-20°C to 55°C

Humidity Range

0%RH to 100%RH

104
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720F Series Wireless Liquid Hand Soap Sensor
R720F series can detect the existence of hand sanitizer/ water leakage. This device is connected with twoelectrode rods which can be used to detect the stateof the insufficient amount of hand sanitizer in thehand sanitizer box or whether there is the waterleakage in the detection area.
※The shape and orientation of electrode rod can beselected according to the needs.

Main Characteristics◼ Liquid hand soap detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Electrode Rod Material

Nickel-plated phosphor bronze

Electrode Rod Length

Total length: 201.5± 1.5mm
10 sections of the electrode rod have beenrolled grooves for easy cutting. The length ofeach section is about 10mm as the figureshown.

Dimension

88mm x W 65mm x H 19mm

R720FLO
L-type probe
electrode rods upward

R720FLD
L-type probe
electrode rods downward

R720FU
U-type probe
105

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720FW Wireless Water Leak Detector
R720FW is a wireless communication device fordetecting water leak.

Main Characteristics◼ Water leak detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Electrode Rod Material

Nickel-plated phosphor bronze

Dimension

88mm x 65mm x 19mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

106
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R720FLT Wireless Toilet Tank Leak Detector
R720FLT is connected with two electrode rods todetect the water make-up of the toilet water tank,detect the daily water make up times and whether thewater tank is faulty.

Main Characteristics◼ Toilet tank leak detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Electrode Rod Material

Nickel-plated phosphor bronze

LengthTotal length: Ø 3mm x 90.2mm(Length from the bottom of the R720FLT unit
to the top of the probe.)
Electrode Rod : Ø 3mm x 73.75mm

Dimension

88mm x 65mm x 19mm

107
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0701/RA0701Y/R72601
Wireless CO Sensor

RA0701

R72601

RA0701Y

RA0701 / RA0701Y / R72601 is a wireless communication device for detecting theconcentration of CO in the air.

Main Characteristics◼ CO concentration detection

Technical Parameter
Input Power
Solar Panel Specification

RA0701

RA0701Y

R72601DC 12VDC 12V

3x18650//

5W/18VDC

CO Measurement Range

0-2000ppm

CO Measurement Method

Electrochemical sensors

CO Measurement
Resolution
CO Measurement
Accuracy

0.1 ppm<± reading 3% (@25°C)

Working Pressure Range

Standard atmospheric pressure ±10%

Main body IP Rating

IP40

IP23

IP23

108
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0708/RA0708Y/R72608
Wireless Water pH Sensor

RA0708RA0708Y

R72608RA0708 / RA0708Y / R72608 is a wireless communication device for detecting thewater pH value and water temperature.

Main Characteristics◼ Water pH detection

Technical Parameter
Input Power
Solar Panel Specification

RA0708RA0708Y

R72608

DC 12VDC 12V

3x18650//

5W/18VDC

0~14PHPH Value Range
Temperature Range

0 to 65° C

Installation Method

Immersive installation, 3/4NPT pipe thread

Wire Length

5 meters, other lengths can be customized

Main body IP Rating

IP40

PH Sensor IP Rating

IP23

IP23

IP68

109
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0710/RA0710Y/R72610
Wireless Water Turbidity Sensor

RA0710RA0710Y

R72610RA0710 / RA0710Y / R72610 is a wireless communication device for detecting thewater turbidity and water temperature.
※ If the user needs a range of 0~100 NTU / 0~20 NTU, the user needs to purchase thesensor of this range

Main Characteristics◼ Water turbidity detection

Technical Parameter
Input Power
Solar Panel Specification

RA0710RA0710Y

R72610DC 12VDC 12V

3x18650//

5W/18VDC

Measurement Range

0~1000 NTU

Accuracy±5% or ±3NTU

Installation Method

Immersive installation, 3/4NPT pipe thread

Wire Length

5 meters, other lengths can be customized

Main body IP Rating

IP40

Turbidity Sensor IP Rating

IP23

IP23

IP68

110
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0711/RA0711Y/R72611
Wireless Water Level Sensor

RA0711

RA0711Y

R72611

RA0711 / RA0711Y / R72611 is a wireless communication device for detecting thewater level.
※ Others line length/range can be customized.

Main Characteristics◼ Water level detection

Technical Parameter
Input Power
Solar Panel Specification

RA0711

RA0711Y

R72611DC 12VDC 12V

3x18650//

5W/18VDC

Measurement Range

10m

Wire Length

12m

Accuracy Level

0.25%FS (typical value)

Main body IP Rating
Water Level Sensor IP Rating

IP40

IP23

IP23

IP68

111
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0715/RA0715Y/R72615/R72615A
Wireless CO2 / Temperature / Humidity Sensor

RA0715

R72615RA0715Y

R72615A

RA0715 / RA0715Y / R72615 / R72615A is a wireless communication device fordetecting the concentration of CO2 in the air.

Main Characteristics◼ CO2, temperature and humidity detection

Technical Parameter
Input Power
Solar Panel Specification

RA0715RA0715Y

R72615

R72615A

DC 12VDC 12V

3x18650

8xER14505//

5W/18VDC/

CO2 Measurement Range

400-5000ppm

Temperature
Measurement Range
Humidity Measurement
Range
Main body IP Rating-20°C~55°C
0%RH ~ 100%RH
IP20

IP43

IP23

IP40

112
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0716/RA0716Y/R72616/R72616A
Wireless PM2.5 / Temperature / Humidity Sensor

RA0716

R72616

RA0716Y

R72616A

RA0716 / RA0716Y / R72616 / R72616A is a wireless communication device fordetecting the PM2.5 dust in the air.

Main Characteristics◼ PM2.5, temperature and humidity detection

Technical Parameter

Input Power
Solar Panel Specification

RA0716

RA0716Y

R72616

R72616A

DC 12VDC 12V

3x18650

8xER14505//

5W/18VDC/

Measurement Range

0.3 ~ 1.0 ; 1.0 ~ 2.5um

Counting Efficiency

50%@0.3um, 98%@≥0.5um

Effective Rang
(PM2.5 standard)
Temperature
Measurement Range
Humidity Measurement
Range

Main body IP Rating

0~500μg/m3-20°C~55°C
0%RH ~ 100%RH

IP20

IP23

IP23

IP30

113
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0723/RA0723Y/R72623
Wireless PM2.5 / Noise / Temperature / Humidity Sensor

RA0723

R72623RA0723YRA0723 / RA0723Y / R72623 is a wireless communication device which can detect
PM2.5, noise intensity, temperature and humidity of the environment.

Main Characteristics◼ PM2.5, noise, temperature and humidity detection

Technical Parameter
Input Power
Solar Panel Specification

RA0723RA0723Y

R72623

DC 12VDC 12V

3x18650//

5W/18VDC

Particle Measurement
Range

PM2.5: 0.3 ~ 1.0 ; 1.0 ~ 2.5um

Counting Efficiency

50%@0.3um, 98%@≥0.5um

Effective Rang
(PM2.5 standard)
Temperature
Measurement Range
Humidity Measurement
Range

0~500μg/m3-20°C~55°C
0%RH~100%RH

Noise Measuring Range
Main body IP Rating

30dB~130dB
IP20

IP23

IP23
114

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0724/RA0724Y/R72624
Wireless Noise / Temperature / Humidity Sensor

RA0724

R72624

RA0724Y

RA0724 / RA0724Y / R72624 is a wireless communication device which can detect
noise intensity, temperature and humidity of the environment.

Main Characteristics◼ Noise, temperature and humidity detection

Technical Parameter
Input Power
Solar Panel Specification

RA0724

RA0724Y

R72624

DC 12VDC 12V

3x18650//

5W/18VDC

Noise Measurement
Range

30dB~130dB

Measuring Error

3% F.S

Frequency Weighted
Characteristic
Temperature
Measurement Range
Humidity Measurement
Range
Main body IP Rating

A weighted-20°C~55°C
0%RH~100%RH
IP40

IP43

IP43

115
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA0730/RA0730Y/R72630
Wireless Wind Speed / Wind Direction / Temperature / Humidity Sensor

RA0730R72630RA0730Y

RA0730 / RA0730Y / R72630 is equipped with wind speed sensor, wind direction
sensor, and temperature and humidity sensor. It can detect and send the data of thewind speed, wind direction, temperature and humidity of the environment.

Main Characteristics◼ Wind speed, wind direction, temperature and humidity detection

Technical Parameter
Input Power
Solar Panel Specification
Wind Speed
Measurement Range
Wind Direction
Measurement Range
Temperature
Measurement Range
Humidity Measurement
Range

RA0730RA0730Y

R72630DC 12VDC 12V

3x18650//

5W/18VDC

0-30m/s
16 points of a compass-20°C~55°C
0%RH~100%RH

116
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R72632A/R726332A01 Wireless Soil NPK Sensor

R72632A01

R72632A

R72632A / R72632A01 can detect and send soil nitrogen (N), phosphorus (P) andpotassium (K) data.
※ It is suitable for measuring ordinary yellow-cinnamon soil, black soil, and terra
rossa.

※ It is not applicable to saline-alkali land, sandy land, or other powdery objects
with high salinity.
※ The soil humidity shall be more than 25%

Main Characteristics◼ Soil NPK detection

Technical Parameter
Input Power

R72632A

R72632A01

2 x ER34615

8 x ER14505

Measurement Range

0-1999 mg/kg

Detection Accuracy±2% F.s

Detection Resolution

1mg/kg (mg/L)

Wire Length

1.25m

Main body IP Rating

IP65

NPK Sensor IP Rating

IP68

117
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA07W Wireless Water Leak Detection and Location Sensor
RA07W is a water leak detector leak locating
equipment, which can be connected to water leaksensor through the external four-core positioning leakdetection sensor line to detect the water leak location.

Main Characteristics◼ Water leak detection◼ IP65

Technical Parameter
Input Power

12V/1A

Wire Length

Water leak detector line 3m+ extension line
1m

Leak Detection Error Range

1% ± 0.5 meters of sensor line length

Dimension

111mm x 86mm x 41mm

Working Temperature-20°C~55°C

Operating Humidity

5%RH~95%RH

Storage Temperature-40°C~85°C

118
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08B01/RA08B01S Wireless CO2 / Temperature / Humidity / TVOC /Light / Air Pressure / PIR Sensor

RA08B01

RA08B01S

RA08B01 / RA08B01S is a multi-functional device for indoor detection of CO2,
temperature, humidity, TVOC, illuminance, air pressure, and PIR.

※ RA08B01S: With a 2.13-inch E-paper display※ Battery power supply

Main Characteristics◼ Built-in sensors:
CO2, Temperature, humidity, TVOC, illuminance, air pressure and PIR.

Technical Parameter
Input Power

4 x 3.6V ER14505 lithium batteries

CO2 Measurement Range

400 to 5000 ppm ±(50ppm+3% of reading)
5001 to 10000ppm ± 10% of reading

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

TVOC Measurement Range

0 to 1,000,000 ppb

Illuminance Range

0.01 Lux to 157 Klux

Air Pressure Measurement Range

300 to 1100hPaPIR Detection Distance

0~2.5m119

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08B02/RA08B02S
Wireless CO2 / Temperature / Humidity / TVOC / PIR Sensor

RA08B02

RA08B02S

RA08B02 / RA08B02S is a multi-functional device for indoor detection of CO2,
temperature, humidity, TVOC and PIR.
※ RA08B02S: With a 2.13-inch E-paper display※ Battery power supply

Main Characteristics◼ Built-in sensor:
CO2, Temperature, humidity, TVOC and PIR.

Technical Parameter
Input Power

4 x 3.6V ER14505 lithium batteries

CO2 Measurement Range

400 to 5000 ppm ±(50ppm+3% of reading)
5001 to 10000ppm ± 10% of reading

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

TVOC Measurement Range

0 to 1,000,000 ppb

PIR Detection Distance

0~2.5m120
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08B03/RA08B03S Wireless CO2 / Temperature / Humidity / TVOC /Light / Air Pressure / PIR / NH3 / H2S Sensor

RA08B03

RA08B03S

RA08B03 / RA08B03S is a multi-functional device for indoor detection of CO2,
temperature, humidity, TVOC , illuminance, air pressure, PIR, NH3 and H2S.
※ RA08B03S: With a 2.13-inch E-paper display※ Battery power supply

Main Characteristics◼ Built-in sensors:
CO2, Temperature, humidity, TVOC , illuminance, air pressure, PIR, NH3 and H2S.

Technical Parameter
Input Power

4 x 3.6V ER14505 lithium batteries

CO2 Measurement Range

400 to 5000 ppm ±(50ppm+3% of reading)
5001 to 10000ppm ± 10% of reading

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

TVOC Measurement Range

0 to 1,000,000 ppb

Illuminance Range

0.01 lux to 157K lux

Air Pressure Measurement Range

300 to 1100hPaPIR Detection Distance

0~2.5mNH3 Measurement Range

0 to 10ppm

H2S Measurement Range

0 to 5ppm
121

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08B04/RA08B04S
Wireless CO2 / Temperature / Humidity / PIR / NH3 / H2S Sensor

RA08B04

RA08B04S

RA08B04 / RA08B04S is a multi-functional device for indoor detection of CO2,
temperature, humidity, PIR, NH3, and H2S.
※ RA08B04S: With a 2.13-inch E-paper display※ Battery power supply

Main Characteristics◼ Built-in sensors:
CO2, Temperature, humidity, PIR, NH3 and H2S.

Technical Parameter
Input Power

4 x 3.6V ER14505 lithium batteries

CO2 Measurement Range

400 to 5000 ppm ±(50ppm+3% of reading)
5001 to 10000ppm ± 10% of reading

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

PIR Detection Distance

0~2.5mNH3 Measurement Range

0 to 10ppm

H2S Measurement Range

0 to 5ppm

122
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08D07/RA08D07S Wireless CO2 / Temperature / Humidity / TVOC /Light / Air Pressure / PIR / CH2O / CO Sensor

RA08D07

RA08D07S

RA08D07 / RA08D07S is a multi-functional device for indoor detection of CO2,
temperature, humidity, TVOC, illuminance, air pressure, PIR, CH2O and CO.
※ RA08D07S: With a 2.13-inch E-paper display※ DC power supply

Main Characteristics◼ Built-in sensors:

CO2, temperature, humidity, TVOC, illuminance, air pressure, PIR and CH2O.
◼ External sensor: CO sensor.

Technical Parameter
Input Power

DC12V

CO2 Measurement Range

400 to 5000 ppm ±(50ppm+3% of reading)
5001 to 10000ppm ± 10% of reading

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

TVOC Measurement Range

0 to 1,000,000 ppb

Illuminance Range

0.01 Lux to 157 Klux

Air Pressure Measurement Range

300 to 1100hPaPIR Detection Distance

0~2.5mCH2O Measurement Range

0-2000ppb

CO Measurement Range

0- 1000ppm

123

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08D08/RA08D08S Wireless PM2.5 / Temperature / Humidity / TVOC /Light / Air Pressure / PIR / CO Sensor

RA08D08

RA08D08S

RA08D08 / RA08D08S is a multi-functional device for indoor detection of PM2.5,
temperature, humidity, TVOC, illuminance, air pressure, PIR and CO.
※ RA08D08S: With a 2.13-inch E-paper display※ DC power supply

Main Characteristics◼ Built-in sensors:
PM2.5, Temperature, humidity, TVOC, illuminance, air pressure and PIR.
◼ External sensor: CO sensor.

Technical Parameter
Input Power

DC12V

PM2.5 Measurement Range

0.3 to 1.0um;
1.0 to 2.5um

Particle Mass Concentration
Effective Range

0 to 500μg/m3

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

TVOC Measurement Range

0 to 1,000,000 ppb

Illuminance Range

0.01 Lux to 157 Klux

Air Pressure Measurement Range

300 to 1100hPaPIR Detection Distance

0~2.5mCO Measurement Range

0- 1000ppm

124

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA08D09/RA08D09S Wireless CO2 / Temperature / Humidity / TVOC /Light / Air Pressure / PIR / NH3 / H2S Sensor

RA08D09

RA08D09S

RA08D09 / RA08D09S is a multi-functional device for indoor detection of CO2,
temperature, humidity, TVOC, illuminance, air pressure, PIR, NH3 and H2S.
※ RA08D09S: With a 2.13-inch E-paper display※ DC power supply

Main Characteristics◼ Built-in sensors:
CO2, Temperature, humidity, TVOC, illuminance, air pressure, PIR, NH3 and H2S.

Technical Parameter
Input Power

DC12V

CO2 Measurement Range

400 to 5000 ppm ±(50ppm+3% of reading)
5001 to 10000ppm ± 10% of reading

Temperature Measurement Range

0°C to 50°C

Humidity Measurement Range

0%RH to 100%RH

TVOC Measurement Range

0 to 1,000,000 ppb

Illuminance Range

0.01 Lux to 157 Klux

Air Pressure Measurement Range

300 to 1100hPaPIR Detection Distance

0~2.5mNH3 Measurement Range

0 to 10ppm

H2S Measurement Range

0 to 5ppm
125

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R211 Wireless IR Blaster
R211 can execute IR learning and IR applying. After IR
learns, it can operate R211 to control electricalequipment remotely, e.g. electric fan and air
conditioner.
※ Infrared frequency 38KHz

Main Characteristics◼ IR learning◼ IP30Technical Parameter
Input PowerDC 12V

Standby Current

50mA

Infrared Frequency

38KHz

Infrared Signal Range

About 32 meters

Dimension

Ø 106mm x 30.5mm

Operating Temperature-20°C~55°C

Operating Humidity

5% RH ~ 95% RH (No condensation)

Storage Temperature-40°C~85°C

126
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311FA/R313FA Wireless Activity Detection Sensor
R311FA / R313FA can detect its sudden movement or
vibration.
※ R311FA Built-in antenna※ R313FA External antenna

Main Characteristics◼ Vibration status: 0(off) or 1(on) detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

40uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Vibration Intensity Sensitivity

62.5mgDimension

R311FA: 57mm x 35mm x 15mm
R313FA: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

127
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311FA1/R313FA1 Wireless Accelerometer
When the R311FA1 / R313FA1 moves or shakes beyond
the set threshold, it immediately reports the current
acceleration and velocity of the X, Y, and Z axes.
※ R311FA1 Built-in antenna※ R313FA1 External antenna

Main Characteristics◼ 3-axis acceleration and velocity detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

42uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Dimension

R311FA1: 57mm x 35mm x 15mm
R313FA1: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

128
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311FB/R313FB Wireless Activity Event Counter
R311FB / R313FB can count its number of movements
or vibrations※ R311FB Built-in antenna※ R313FB External antenna

Main Characteristics◼ Vibration count detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

40uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Vibration Intensity Sensitivity

62.5mgDimension

R311FB: 57mm x 35mm x 15mm
R313FB: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

129
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R311FC/R313FC Wireless Activity Timer
R311FC / R313FC detects the duration of the
movement or vibration.
※ R311FC Built-in antenna※ R313FC External antenna

Main Characteristics◼ Vibration duration time detection◼ IP30Technical Parameter
Input Power

2 x 3.0V CR2450 button batteries

Operating Voltage

2.4V to 3.0V

Standby Current

42uA/3.0V

Transmitting Current (max)

120mA/3.0V

Receiving Current (max)

11mA @3.0V

Battery Accuracy± 0.1V

Vibration Intensity Sensitivity

62.5mgDimension

R311FC: 57mm x 35mm x 15mm
R313FC: 57mm x 38.05mm x 15mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

130
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R716S Portable LoRa Field Signal Meter
R716S is developed based on LoRa technology todetect the network signal of the LoRa network.
R716S can detect the LoRa signal strength of thescanned area and display the detected data through
LCD.

Main Characteristics◼ LoRa signal strength detection

Technical Parameter
Input Power

2 AA size alkaline battery

Operating Voltage Range

2.3V to 3V

Low Battery Threshold

2.4V

Battery Voltage Accuracy± 0.1V

Standby Current

28uA

Dimension

112mm x 34mm x 17mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

131
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718E/R718EC Wireless Accelerometer and Surface Temperature Sensor
R718E / R718EC reports 3-axis acceleration, velocity,
angle, status, and surface temperature as the values of
movement and vibration exceed the thresholds.
The thresholds of each axis can be set based on user's
needs and different applications.

Main Characteristics◼ 3-axis acceleration, velocity, angle detection◼ Surface temperature detection◼ Main body-IP65, Sensor-IP67

Technical Parameter
R718E

R718EC

Vibration sensor

Internal

External

Input Power

2 x 3.6V ER14505 lithium batteries

3-axis Acceleration Range
Angle Range±16g±90° (Unit:0.005°)

ADC Maximum Resolution

13 bits

Temperature Measurement
Range-40°C~120°C

Dimension

112 mm x 88 mm x 32 mm

Operating Temperature-20°C~55°C

Operating Humidity Range<90% RH (No condensation)

Storage Temperature Range-40°C~85°C

132
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718EA/R718EB Wireless Tilt Angle (and Surface Temperature) Sensor
R718EA / R718EB reports 3-axis angle and surface
temperature as the values of movement and vibration
exceed the thresholds.
R718EA is connected with an external NTC thermistor
to detect the surface temperature of the measured
object.

Main Characteristics◼ Angle of the 3-axis detection◼ Surface temperature detection◼ Main body-IP65, Sensor-IP67

Technical Parameter
R718EA

R718EBNTC Thermistor

40°C~120°C

X

Angle Resolution

1°

0.1° / 0.005°

Input Power

2 x 3.6V ER14505 lithium batteries

Angle Measurement Range±90°

Angle Accuracy±3°

Dimension

112 mm x 88 mm x 32 mm

Operating Temperature-20°C~55°C

Operating Humidity Range<90% RH (No condensation)

Storage Temperature Range-40°C~85°C※ The units of R718EB’s angle measurement are 0.1° and 0.005°.
The unit cannot be changed through the configuration of commands.
It shall be set before the shipment.

133
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718IA/R718IA2 Wireless 1/2-Input 0-5V ADC Sampling Interface
R718IA / R718IA2 can externally connect a device tomeasure ADC voltage, and the measuring range is 0
to 5v.

Main Characteristics◼ ADC 0-5V detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

ADC Sampling Voltage Range

0-5V

ADC Resolution

12 bits

ADC Conversion Rate

1.14 Msps

External Cable Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

134
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718IB/R718IB2 Wireless 1/2-Input 0-10V ADC Sampling Interface
R718IB / R718IB2 can externally connect a device tomeasure ADC voltage, and the measuring range is 0
to 10v.

Main Characteristics◼ ADC 0-10V detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

ADC Sampling Voltage Range

0-10V

ADC Resolution

12 bits

ADC Conversion Rate

1.14 Msps

External Cable Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

135
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718J/R718J2 Wireless 1/2-Input Dry Contact Interface
R718J / R718J2 can connect a dry contact device todetect output status, e.g. switch, reed switch and soon.

Main Characteristics◼ Dry contact detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Wire material

UL2547 28AWG

Wire length

1000mm（±5mm）

Wire flame resistance rating

VW-1

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

136
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718H/R718H2 Wireless 1/2-Input Pulse Counter Interface
R718H / R718H2 is connected with a pulse detection
interface, which can calculate the number of pulses.
※ The input pulse width is greater than 100ms toaccurately count.

Main Characteristics◼ Pulse counter detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Pulse Voltage Range

2.4v~3.3v

Dimension

112mm x 88mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

137
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718LB/R718LB2
Wireless 1/2-Gang Hall Type Open / Close Detection Sensor
R718LB / R718LB2 is equipped with a hall sensor,
which can be used for door and window switch state
detection.

Main Characteristics◼ Open / Close detection◼ Main body-IP65/IP67, Sensor-IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Performance Characteristics

All-pole sensing, the magnet can activate
either pole.

Hall Sensor Sensing DistanceLess than 3cm.

Cable Length

1mDimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

138
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718MA Wireless Asset Sensor
R718MA has a simple positioning function which candetect the position status of itself. The device canreport RSSI and SNR information to the gateway forprocessing periodically and locating its position.

Main Characteristics◼ RSSI and SNR detection◼ Simple positioning◼ Main body-IP65/IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

139
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718MBA Wireless Activity Detection Sensor
R718MBA can detect its sudden movement or
vibration.

Main Characteristics◼ Vibration status: 0(off) or 1(on) detection◼ Main body-IP65/IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Standby Current

76uA

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

140
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718MBB Wireless Activity Event Counter
R718MBB can count its number of movements orvibrations.

Main Characteristics◼ Vibration count detection◼ Main body-IP65/IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Standby Current

76uA

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

141
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718MBC Wireless Activity Timer
R718MBC detects the duration of the movement or
vibration.

Main Characteristics◼ Vibration duration time detection◼ Main body-IP65/IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Standby Current

76uA

Dimension

112mm x 65mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

142
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718KA/R718KA2
Wireless 1/2-Gang mA Current Meter Interface, 4~20mA
R718KA / R718KA2 It converts the 4mA-20mA signal
into a corresponding detection signal through theoperational amplifier and then reads the current
through the sampling of the ADC module.

Main Characteristics◼ 4~20mA current detection◼ IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Operating Voltage

3.1V to 3.65V

Measurement Range

4~20mA

Dimension

112mm x 88mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

143
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718KBA Wireless 4-Input 0-10V ADC Sampling Interface
R718KBA is a device for detecting 0-10V signals
interface. It can detect four 0-10V signals
simultaneously, with high precision and small error.
It is suitable for use with sensors or instruments that
output signals in the range of 0-10V.

Main Characteristics◼ 4-Input 0-10V ADC Sampling Interface◼ IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Measurement Range

0 to 10V

Accuracy

0V to 0.5V: <2%
0.5V to 10V: <1%

Resolution

1mV

Cable Length

1mDimension

112mm x 88mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

144
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718KBB Wireless 4-Input 0-20mA Sensor Interface
R718KBB is a device for detecting 0-20mA signals
interface. It can detect four 0-20mA signals
simultaneously, with high precision and small error.
It is suitable for use with sensors or instruments that
output signals in the range of 0-20mA.

Main Characteristics◼ 0~20mA current detection◼ IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Measurement Range

0 to 20mA

Accuracy

0 to 1mA: <2%
1 to 20mA: <1%

Resolution

1uA

Cable Length

1mDimension

112mm x 88mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

145
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718KBC
Wireless 2-Input 0-10V ADC Sampling and 2-Input 0-20mA Sensor Interface
R718KBC is a device for detecting 0-10V and 0-20mA
signals interface. It can detect two 0-10V and two 020mA signals simultaneously, with high precision andsmall error.
It is suitable for use with sensors or instruments that
output signals in the range of 0-10V and 0-20mA.

Main Characteristics◼ 0-10V ADC and 4~20mA current detection◼ IP67

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

Measurement Range

0 to 10V
0 to 20mA

Accuracy

0V to 0.5V: <2%
0.5V to 10V: <1%
0 to 1mA: <2%
1 to 20mA: <1%

Resolution

1mV / 1uA

Cable Length

1mDimension

112mm x 88mm x 32mm

Weight141g

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

146
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PC Wireless RS485 Adapter
R718PC supports RS485 serial port transparent
transmission.
The device can send the read commands to sensors
supporting RS485 protocol according to the configured
cycle.
※ It supports up to 128 bytes of data (depending on
the current communication rate)

Main Characteristics◼ RS485 serial port transparent transmission◼ Main body-IP65/IP67

Technical Parameter
Input PowerDC 12V power supply

Operating Current

35 mA (when there is no external sensor)

Baud Rate

115200 / 57600 / 38400 / 28800 / 19200 /
9600 / 4800 / 2400

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

147
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718PDA Wireless RS232 Adapter
R718PDA supports RS232 serial port transparent
transmission.
The device can send the read commands to sensors
supporting RS232 protocol according to the configured
cycle.
※ It supports up to 128 bytes of data (depending on
the current communication rate)

Main Characteristics◼ RS232 serial port transparent transmission◼ Main body-IP65/IP67

Technical Parameter
Input PowerDC 12V power supply

Operating Current

45 mA (when there is no external sensor)

Baud Rate

115200 / 57600 / 38400 / 28800 / 19200 /
9600 / 4800 / 2400

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

148
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N17/R718N17E/R718N17D/R718N17DE
Wireless Single-Phase Current Meter with 1 x 75A Clamp-On CT

R718N17

R718N17E

R718N17D

R718N17DE

R718N17 series is a 1-phase clamp-on CT of 75A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 100mA~75A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N17
Input PowerCT cables
Measurement Range

R718N17E

R718N17D

2 x ER14505
Undetachable

R718N17DE

DC 12V

Detachable

Undetachable

Detachable

100mA~75A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter10±0.2 mm

149
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N115/R718N115E/R718N115D/R718N115DE
Wireless Single-Phase Current Meter with 1 x 150A Clamp-On CT

R718N115

R718N115E

R718N115D

R718N115DE

R718N115 series is a 1-phase clamp-on CT of 150A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 1A~150A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N115
Input PowerCT cables

R718N115E

R718N115D R718N115DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

Measurement Range

1A~150A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

16±0.5 mm

150
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N125/R718N125E/R718N125D/R718N125DE
Wireless Single-Phase Current Meter with 1 x 250A Clamp-On CT

R718N125

R718N125E

R718N125D

R718N125DE

R718N125 series is a 1-phase clamp-on CT of 250A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 1A~250A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N125
Input PowerCT cables

R718N125E

R718N125D R718N125DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

Measurement Range

1A~250A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

24.3±0.5 mm

151
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N163/R718N163E/R718N163D/R718N163DE
Wireless Single-Phase Current Meter with 1 x 630A Clamp-On CT

R718N163

R718N163E

R718N163D

R718N163DE

R718N163 series is a 1-phase clamp-on CT of 630A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 5A~630A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N163
Input PowerCT cables

R718N163E

R718N163D R718N163DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

Measurement Range

5A~630A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

35±0.5 mm

152
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N1100/R718N1100E/R718N1100D/R718N1100DE
Wireless Single-Phase Current Meter with 1 x 1000A Clamp-On CT

R718N1100

R718N1100E

R718N1100D

R718N1100DE

R718N1100 series is a 1-phase clamp-on CT of 1000A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 10A~1000A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N1100
Input PowerCT cables
Measurement Range

R718N1100E R718N1100D R718N1100DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

10A~1000A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

51 mm

153
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N1300/R718N1300E/R718N1300D/R718N1300DE
Wireless 3-Phase Current Meter with 1 x 3000A Clamp-On CT

R718N1300

R718N1300E

R718N1300D

R718N1300DE

R718N1300 series is a 1-phase clamp-on CT of 3000A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 150A~3000A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N1300
Input PowerCT cables
Measurement Range

R718N1300E R718N1300D R718N1300DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

150A~3000A

Resolution

1mA

Wiring Length

About 980mm

CT Hole Diameter

76.8x130mm

154
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N37/R718N37E/R718N37D/R718N37DE
Wireless 3-Phase Current Meter with 3 x 75A Clamp-On CT

R718N37

R718N37E

R718N37D

R718N37DE

R718N37 series is a 3-phase clamp-on CT of 75A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 100mA~75A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N37
Input PowerCT cables
Measurement Range

R718N37E

R718N37D

2 x ER14505
Undetachable

R718N37DE

DC 12V

Detachable

Undetachable

Detachable

100mA~75A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter10±0.2 mm

155
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N315/R718N315E/R718N315D/R718N315DE
Wireless 3-Phase Current Meter with 3 x 150A Clamp-On CT

R718N315

R718N315E

R718N315D

R718N315DE

R718N315 series is a 3-phase clamp-on CT of 150A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 1A~150A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N315
Input PowerCT cables

R718N315E

R718N315D R718N315DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

Measurement Range

1A~150A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

16±0.5 mm

156
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N325/R718N325E/R718N325D/R718N325DE
Wireless 3-Phase Current Meter with 3 x 250A Clamp-On CT

R718N325

R718N325E

R718N325D

R718N325DE

R718N325 series is a 3-phase clamp-on CT of 250A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 1A~250A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N325
Input PowerCT cables

R718N325E

R718N325D R718N325DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

Measurement Range

1A~250A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

24.3±0.5 mm

157
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N363/R718N363E/R718N363D/R718N363DE
Wireless 3-Phase Current Meter with 3 x 630A Clamp-On CT

R718N363

R718N363E

R718N363D

R718N363DE

R718N363 series is a 3-phase clamp-on CT of 630A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 10A~630A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N363
Input PowerCT cables
Measurement Range

R718N363E

R718N363D R718N363DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

10A~630A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

35±0.5 mm

158
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N3100/R718N3100E/R718N3100D/R718N3100DE
Wireless 3-Phase Current Meter with 3 x 1000A Clamp-On CT

R718N3100

R718N3100E

R718N3100D

R718N3100DE

R718N3100 series is a 3-phase clamp-on CT of 1000A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 10A~1000A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N3100
Input PowerCT cables
Measurement Range

R718N3100E R718N3100D R718N3100DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

10A~1000A

Resolution

1mA

Wiring Length

Undetachable cable: About 900mm
Detachable cable: About 1200mm

CT Hole Diameter

51mm

159
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N3300/R718N3300E/R718N3300D/R718N3300DE
Wireless 3-Phase Current Meter with 3 x 3000A Clamp-On CT

R718N3300

R718N3300E

R718N3300D

R718N3300DE

R718N3300 series is a 3-phase clamp-on CT of 3000A , which can be conveniently
connected to the measuring device.
Depending on your needs, you can choose between battery or DC 12V power supply
and choose whether to detach the CT cable.
※ Only support AC current measuring.

Main Characteristics◼ 150A~3000A current detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
R718N3300
Input PowerCT cables
Measurement Range

R718N3300E R718N3300D R718N3300DE

2 x ER14505
Undetachable

DC 12V

Detachable

Undetachable

Detachable

150A~3000A

Resolution

1mA

Wiring Length

About 980mm

CT Hole Diameter

76.8x130mm

160
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718N360/R718N360D
Wireless 3-Phase Current Meter Interface

R718N360

R718N3630D

R718N360 / R718N360D is a 3-phase current detection device. The device provides 3way wiring. Each wiring can be connected with a current transformer provided by thecustomer.
※ Only support AC current measuring.

Main Characteristics◼ Current Meter Interface◼ Main body-IP53

Technical Parameter
Input PowerR718N360

R718N360D

2 x ER14505

DC 12V

It is recommended that the primary side current be at
CT Measurement Range most 600A, and the secondary side current of thecurrent transformer is at most 1A.

Current Resolution
DimensionOperating Temperature

1mA
112mm x 88mm x 32mm
-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

161
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718NL17/R718NL37 Wireless Light Sensor and 1/3-Phase Current Meter
with 75A Clamp-On CT
R718NL17 / R718NL37 is a 1-phase/3-phase clamp-on
CT of 75A with a light sensor, allowing it to beconveniently connected to the measuring device and to
detect environmental illumination.
※ Only support AC current measuring.

Main Characteristics◼ 100mA~75A current detection◼ Illuminance detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
Input Power2 x ER14505

Measurement Range

100mA~75A

Resolution

1mA

Wiring Length

About 900mm

CT Hole Diameter10±0.2 mm

Illuminance Range

0.01 LUX~157K LUX

Illuminance Accuracy± 20%: Under sunlight.
± 10%: Under stable and controlled light source
conditions, such as white LED lamp, 6500K, room
temperature.

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

162
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718NL115/R718NL315 Wireless Light Sensor and 1/3-Phase Current
Meter with 150A Clamp-On CT
R718NL115 / R718NL315 is a 1-phase/3-phase clampon CT of 150A with a light sensor, allowing it to beconveniently connected to the measuring device and to
detect environmental illumination.
※ Only support AC current measuring.

Main Characteristics◼ 1A~150A current detection◼ Illuminance detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
Input Power2 x ER14505

Measurement Range

1A~150A

Resolution

1mA

Wiring Length

About 900mm

CT Hole Diameter

16±0.5 mm

Illuminance Range

0.01 LUX~157K LUX

Illuminance Accuracy± 20%: Under sunlight.
± 10%: Under stable and controlled light source
conditions, such as white LED lamp, 6500K, room
temperature.

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

163
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718NL125/R718NL325 Wireless Light Sensor and 1/3-Phase Current
Meter with 250A Clamp-On CT
R718NL125 / R718NL325 is a 1-phase/3-phase clampon CT of 250A with a light sensor, allowing it to beconveniently connected to the measuring device and to
detect environmental illumination.
※ Only support AC current measuring.

Main Characteristics◼ 1A~250A current detection◼ Illuminance detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
Input Power2 x ER14505

Measurement Range

1A~250A

Resolution

1mA

Wiring Length

About 900mm

CT Hole Diameter

24.3±0.5 mm

Illuminance Range

0.01 LUX~157K LUX

Illuminance Accuracy± 20%: Under sunlight.
± 10%: Under stable and controlled light source
conditions, such as white LED lamp, 6500K, room
temperature.

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

164
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718NL163/R718NL363 Wireless Light Sensor and 1/3-Phase Current
Meter with 630A Clamp-On CT
R718NL163 / R718NL363 is a 1-phase/3-phase clampon CT of 630A with a light sensor, allowing it to beconveniently connected to the measuring device and to
detect environmental illumination.
※ Only support AC current measuring.

Main Characteristics◼ 5A~630A /10A~630A current detection◼ Illuminance detection◼ Main body-IP53, Sensor-IP30

Technical Parameter
Input Power2 x ER14505

Measurement Range

R718NL163: 5A~630A
R718NL363: 10A~630A

Resolution

1mA

Wiring Length

About 900mm

CT Hole Diameter

35±0.5 mm

Illuminance Range

0.01 LUX~157K LUX

Illuminance Accuracy± 20%: Under sunlight.
± 10%: Under stable and controlled light source
conditions, such as white LED lamp, 6500K, room
temperature.

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

165
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R718IJK Wireless Multi-Sensor Interface for 0-24V ADC, Dry Contact and
4-20mA Sensors
R718IJK can detect 4mA-20mA signal, 0-24V ADC
sampling signal and dry contact input signal.

Main Characteristics◼
◼
◼
◼

4mA-20mA Current Meter Interface
0-24V ADC Sampling Interface
Dry contact Interface
IP65

Technical Parameter
Input Power

2 x 3.6V ER14505 lithium batteries

ADC Measurement Range

0~24v

Current Measurement
Range

4~20mA

Dimension

112mm x 88mm x 32mm

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

166
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RP02RH1PN063/RP02RH1PNLB063 Wireless 1P+N Miniature Circuit
Breaker with Power Meter (and Leak Detection), 63A (with 30mA sensitivity)

RP02RH1PN063

RP02RH1PNLB063

RP02RH1PN063 / RP02RH1PNLB063 is a class C smart 1P+N Miniature Circuit Breakerwith Power Meter (and Leak Detection) based on LoRaWAN open protocol. It canmonitor the status of all external circuit breakers in real time.

Main Characteristics◼ Miniature Circuit Breaker (MCB)◼ Current, voltage, power, temperature, energy (,leakage current) detection◼ Circuit breaker status detection

Technical Parameter
LoRa Radio Module Power Supply

DC12V

Power Module Power Supply

AC 110 to 240V / 24W / 50Hz

Power Module Certified

UL, CB, CE, UKCA, TUVBreaker Rated Voltage

AC230V/50Hz

Breaker Rated Current

63A

Residual Current

1PNL: 30mA

Environment Temperature Range-20°C~55°C

Environment Humidity Range<90% RH (No condensation)

Storage Temperature Range-40°C~85°C
167

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RP02RH3PN063/RP02RH3PNLB063 Wireless 3P+N Miniature Circuit
Breaker with Power Meter (and Leak Detection), 63A (with 30mA sensitivity)

RP02RH3PN063

RP02RH3PNLB063

RP02RH3PN063 / RP02RH3PNLB063 is a class C smart 3P+N Miniature Circuit Breakerwith Power Meter (and Leak Detection) based on LoRaWAN open protocol. It canmonitor the status of all external circuit breakers in real time.

Main Characteristics◼ Miniature Circuit Breaker (MCB)◼ Current, voltage, power, temperature, energy (,leakage current) detection◼ Circuit breaker status detection

Technical Parameter
LoRa Radio Module Power Supply

DC12V

Power Module Power Supply

AC 110 to 240V / 24W / 50Hz

Power Module Certified

UL, CB, CE, UKCA, TUVBreaker Rated Voltage

AC400V

Breaker Rated Current

63A

Residual Current

3PNL: 30mA

Environment Temperature Range-20°C~55°C

Environment Humidity Range<90% RH (No condensation)

Storage Temperature Range-40°C~85°C

168
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RP02RH2P100/RP02RH4P100
Wireless 2P/4P Miniature Circuit Breaker with Power Meter, 100A

RP02RH2P100

RP02RH4P100

RP02RH2P100 / RP02RH4P100 is a class C smart 2P/4P Miniature Circuit Breaker with
Power Meter based on the LoRaWAN open protocol. It can monitor the status of all
external circuit breakers in real time. When the wire is abnormal, such as undervoltage,
overvoltage, overload, etc., the system will automatically warn, alarm, and power off. It
can also periodically detect the electricity, current, voltage, power, circuit breakerstatus, etc. of all external short circuit breakers.

Main Characteristics◼ Miniature Circuit Breaker (MCB)◼ Current, voltage, power, temperature, energy detection◼ Circuit breaker status detection

Technical Parameter
LoRa Radio Module Power Supply

DC12V

Power Module Power Supply

AC 110 to 240V / 24W / 50Hz

Power Module Certified

UL, CB, CE, UKCA, TUVBreaker Rated Voltage

2P: AC230V
4P: AC400V

Breaker Rated Current

100A

Environment Temperature Range-20°C~55°C

Environment Humidity Range<90% RH (No condensation)

Storage Temperature Range-40°C~85°C
169

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RP02RH3P250/RP02RH4P250
Wireless 3P/4P Miniature Circuit Breaker with Power Meter, 250A

RP02RH3P250

RP02RH4P250

RP02RH3P250 / RP02RH4P250 is a class C smart 3P/4P Miniature Circuit Breaker with
Power Meter based on the LoRaWAN open protocol. It can monitor the status of all
external circuit breakers in real time. When the wire is abnormal, such as undervoltage,
overvoltage, overload, etc., the system will automatically warn, alarm, and power off. It
can also periodically detect the electricity, current, voltage, power, circuit breakerstatus, etc. of all external short circuit breakers.

Main Characteristics◼ Miniature Circuit Breaker (MCB)◼ Current, voltage, power, temperature, energy detection◼ Circuit breaker status detection

Technical Parameter
LoRa Radio Module Power Supply

DC12V

Power Module Power Supply

AC 85 to 264V / 60W / 47 to 63Hz

Power Module Certified

UL ,CB, CE, UKCA, TUVBreaker Rated Voltage

AC400V

Breaker Rated Current

250A

Environment Temperature Range-20°C~55°C

Environment Humidity Range<90% RH (No condensation)

Storage Temperature Range-40°C~85°C
170

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RA10 Wireless Valve Controller
RA10 can control the open/close status of the valve
remotely or manually, such as water valve, gas valve
and ball valve.
※ Apply to the pipe of diameter less than 26.5mm.

Main Characteristics◼ Control valvesTechnical Parameter
Input PowerDC 12V

Actuating Arm Maximum Torque7.5 kgf

Rotation Angle

90 degrees

Physical Size

152.99mm x 70.99mm x128.3mm

Applicable Pipe Diameter6 British inch (3/4 US inch)

Operating Temperature-20°C~55°C

Operating Humidity<90% RH (No condensation)

Storage Temperature-40°C~85°C

171
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R809A/R809A01 Wireless Plug-and-Play Power Outlet with Consumption
Monitoring (and Power Outage Detection)

R809AB/R809AB01(US type)

R809AF(EU type)

R809AG/R809AG01(UK type)

R809AI/R809AI01(AU type)

R809A / R809A01 can remotely or manually control (turn on/off) the connected
electrical equipment. It will report the on/off, energy, voltage, current, power, overcurrent alarm, power off alarm of the load.
※ R809A supports the following types: US, EU, UK and AU type.
※ R809A01 supports the following types: US, UK and AU type.

Main Characteristics◼ On/off, energy, voltage, current, power, over current alarm detection◼ R809A01 supports power off alarm.

Technical Parameter
Input Power

100-240VAC, 50/60Hz

Typical Operating Current

15mA/220VAC/1W

Typical Load Characteristics

Resistive load: 16A/250VAC; P: 4000VA
Inductive load: 8A/220VAC; P: 1760VA(COSφ=0.4)
Rated Load:
US type: 15A/125VAC
EU type: 16A/250VAC
UK type: 13A/250VAC
AU type: 10A/250VAC

Energy Measurement Error

±1%
172

Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R816B/R816B01 Wireless Wall-Mounted Power Socket with Consumption
Monitoring (and Power Outage Detection)
R816B / R816B01 is an electrical switch socket designed
for indoor use. It is compatible with US standard wallcassette installation. The output socket accommodates
US standard 2 or 3 pole plugs.
※ The upper socket is a general socket and cannot be
controlled.
※ The lower socket is a relay control output, with apower detection function.

Main Characteristics◼ On/off, energy, voltage, current, power, over current alarm detection◼ R816B01 supports power off alarm.

Technical Parameter
Input Power

100-240VAC, 50/60Hz

Typical Operating Current

13mA/120VAC/0.8W

Typical Load Characteristics

Resistive load: 16A/250VAC; P: 4000VA
Inductive load: 8A/220VAC; P: 1760VA(COSφ=0.4)

Current Measurement Range

100mA~15A

Energy Measurement Error±1%

Dimension

113.0 mm x 69.0 mm x 39.5 mm

Operating Humidity Range

5% to 85% RH (no condense)

Operating Temperature-10°C~50°C

Storage Temperature-40°C~85 °C

173
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

R831 Wireless Multifunctional Control Box
R831 can be equipped with a three-way controllable
relay switch and three-way relay output can be used as adry contact.
R831 has three operating modes corresponding to thethree keys of the DIP switch.

Main Characteristics◼ R831B - Button mode
◼ R831C - Relay mode
◼ R831D - Relay mode

Technical Parameter
Input PowerDC 12V

Relay Load Characteristics

DC30V/5A (contact load)

Relay Power Consumption

300mW

Relay Type

Magnetic Latching Relay

Dimension

66mm x 47mm x 20.3 mm

Working Temperature-20°C~55°C

Ambient Humidity Range<90% RH (no condense)

Storage Temperature Range-40°C~85°C

174
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

RB02B/RB02C/RB02I Wireless 1/2/3-Gang Push Button Sensor

RB02B

RB02C

RB02I

RB02B/RB02C/RB02I is a button device capable of detecting button presses.

※ The pressing time of the alarm button can be configured through the command.

Main Characteristics◼ Push button status detection◼ IP40Technical Parameter
Input Power2 x 1.5V AAA batteries

Operating Voltage

2.3V to 3V

Dimension

82mmx82mmx15mm

Working Temperature-20°C~55°C

Storage Temperature-40°C~85°C

Operating Humidity<90%RH

175
Available Frequency : EU863-870 / US902-928 / AU915-928 / KR920-923 / AS923-1 /AS923-2 / AS923-3 / IN865-867 / CN470-510

DSC100C Indoor Renewable Energy Power Bank for IoT - USB-C Version
DSC100C is a renewable power bank with a 55mm x100mm dye-sensitized module, two 250F lithium
capacitors, the IP65 of water resistance rating, and an
LED light to indicate the power of the device. The
DSC100C can be charged through indoor light resources
and supply power to IoT devices with low power
consumption.
※ Do not expose to direct sunlight or high temperatures.

Main Characteristics◼
◼
◼
◼

Power Netvox’s and third-party devices thorough Type-C
Adjustable bracket to change the angle of module
The DSC100C can be charged through indoor light
Connect in parallel to support high power-consuming devices and receive
frequent report◼ The user can switch to choose the output voltage

Technical Parameter
Power Supply

2 lithium capacitors in parallel

Operating Voltage

2.5V~3.3V or 2.5V~3.8V
Note: Use switch to choose the output voltage

Dimensions

129.4mm x 90mm x 25mm

Three DSC100C connected in parallel

Two DSC100C connected to a device
176

DSC100C4 Indoor Renewable Energy Power Bank for IoT with 4 Lithium-ion
Capacitors - USB-C Version
DSC100C4 is a renewable power bank with a 55mm x100mm dye-sensitized module, four 250F lithium
capacitors, the IP65 of water resistance rating, and an
LED light to indicate the power of the device. The
DSC100C4 can be charged through indoor light resources
and supply power to IoT devices with low power
consumption.
※ Do not expose to direct sunlight or high temperatures.

Main Characteristics◼
◼
◼
◼

Power Netvox’s and third-party devices thorough Type-C
Adjustable bracket to change the angle of module
The DSC100C4 can be charged through indoor light
Connect in parallel to support high power-consuming devices and receive
frequent report◼ The user can switch to choose the output voltage

Technical Parameter
Power Supply

4 lithium capacitors in parallel

Operating Voltage

2.5V~3.3V or 2.5V~3.8V
Note: Use switch to choose the output voltage

Dimensions

129.4mm x 90mm x 25mm

back

The DSC100C4 connected to a device
177

DSC716L Illuminance Meter
DSC716L detects the illuminance and displays thedata on LCD. You can easily know the illuminanceand find your device a good installation spot by
one short press.

Main Characteristics◼ Illuminance detection

Technical Parameter
Power Supply

2 AA size alkaline batteries (1.5 V/ section)

Operating Voltage

2.3V to 3V

Illuminance Range

0.01 LUX to 157K LUX

Illuminance Accuracy
Dimensions±10% (in white LED light or 6500k light, and at room
temperature )±20% (in the sunlight)
112 mm x 34 mm x 7 mm

178

R100H Wireless LoRa Module
The R100H is a low power transceiver based on the SX1276
chip LoRaTM solution. The R100H is designed for SMD tomount on the main PCB. SMD installations provide the best
RF performance at the lowest cost. In addition, the R100H is
designed to take up minimal board space on the host PCB
which has already included a rich set of interface ports andpower management circuitry. As a result, it can be easily
integrated into other devices without the need for RF
experience and expertise. The R100H operates in the 8621020MHz band.

Main Characteristics◼ High performance and low power 32-bit ARM Cortex-M0 microprocessor◼ Provide powerful and flexible development tools

Technical Parameter
Data Transfer Rate

0.3kbps～50kbps (LoRa) / 1.2kbps～300kbps (FSK)

Bandwidth862-928MHz

Modulation

LoRa/FSK (Remarks: Choose one of them)Receive Sensitivity-121dBm(Frequency deviation=5kHz,Bit Rate=1.2kb/s)Operating Voltage

1.8 to 3.6 V DC

Receiving Current

11mA (typical value)

Emission Current

120mA (typical value)

Working Current

2mA (typical value)Standby Current

8uA

Product Size

16.0mm x 24.5mm x 3.0mm

179

R100L Wireless LoRa Module
The Lora RF module R100L from NETVOX is a low-powertransceiver based on the SX1276 chip LoRaTM solution. The
R100L is designed for SMD to mount on the main PCB. SMD
installations provide the best RF performance at the lowest
cost. In addition, the R100L is designed to take up minimalboard space on the host PCB which has already included arich set of interface ports and power management circuitry.
As a result, it can be easily integrated into other devices
without the need for RF experience and expertise. The
R100L operates in the 470-510MHz band.

Main Characteristics◼ High performance and low power 32-bit ARM Cortex-M0 microprocessor◼ Provide powerful and flexible development tools

Technical Parameter
Data Transfer Rate

0.3kbps～50kbps (LoRa) / 1.2kbps～300kbps (FSK)

Bandwidth

470-510MHz

Modulation

LoRa/FSK (Remarks: Choose one of them)Receive Sensitivity-121dBm(Frequency deviation=5kHz,Bit Rate=1.2kb/s)Operating Voltage

1.8 to 3.6 V DC

Receiving Current

11mA (typical value)

Emission Current

120mA (typical value)

Working Current

2mA (typical value)Standby Current

8uA

Product Size

16.0mm x 24.5mm x 3.0mm

180

R

NETVOX TECHNOLOGY CO., LTD.
TEL: 886-6-2617641
FAX: 886-6-2656120
E-mail: sales@netvox.com.tw
WEB: www.netvox.com.tw

NETVOX TECHNOLOGY CO., LTD (XIAMEN)
TEL: 86-592-5717188
FAX: 86-592-5717180
E-mail: dyx@netvox.com.cn
WEB: www.netvox.com.cn

All specifications are subjected to change with prior notice