Gas Detection

Touchpoint Plus
TMA whole new control experienceTouchpoint Plus
TMTouchpoint Plus brings a whole new control experience to your small system of gas detectors. TouchpointPlus is an easily configurable, wall-mounted control system that supports up to 16 gas detection channels.
Its modular approach enables you to take control and configure what you need for a wide range ofapplications.

Delivering Reliable Control• Honeywell reliability from themost trusted experts in gasdetection• Built-in battery backup forconstant uptime• Robust, shockproof housingfor a wide range of industrial
environments
Flexible Capabilities• Compatible with the full rangeof Honeywell gas detectors• Powered audiovisual alarms
simplify field installation• Configuration includes easy
grouping and voting alarm logic
without specialist knowledge• Next-generation compatibility• Optional Modbus output for
integration with a higher levelsystem
Providing Ease and Efficiency• Quick and easy installation,
configuration, setup,
and maintenance• Easy diagnostics, data,
and reporting• Minimum training time
• Large color touchscreen LCD• Multilingual functionality• Green-yellow-red statusat a glance

The signature feature of the Touchpoint line is a user-friendly touchscreen interface,which the Touchpoint Plus takes to a new level. With this unique interface, it’s easierthan ever to see the status of your system at a glance - maximizing the time you haveto make the right decisions. The intuitive, multilingual interface simplifies operation
and reduces training requirements. The full-color stoplight-style status indication
provides clarity from a distance too.
Touchpoint Plus features a comprehensive set of outputs as standard, includingcommon alarms and dedicated drives for remote audiovisual indicators. Its
modularity enables you to customize your system to meet your specific application
requirements. Selecting the right detector for use with your controller can deliversignificant savings in startup costs and ongoing operations. Our global partner
network and dedicated application specialists are able to help you make the rightchoices for your industry.

With everything at your fingertips, you can take ownership of yoursystem and operate it with confidence, helping to ensure the safetyof your people and the productivity of your site.

Unique User Experience
Taking the user experience to a whole new level
Want tofully utilize
your controller?

Want peaceof mind?

Built for ease –so you can operate itwith confidence

Engineered to the highest
standards of quality andreliability

Want a simple
end-to-end
solution?

Want tosimplify systemsetup?

Easy ordering, installation,and servicing from thegas detection experts

With the intuitive,
ergonomic touchscreen,
setup couldn’t
be easierWant to makefast, informed
decisions?
System status at a glance
when time is critical

Want toknow what’s
going on?
View real-time andhistorical data, analyze
readings, andmuch more

Large color
touchscreen LCD
with multilingual
options
Clear common
status indicators(green, yellow, red)
Built-in sounderMute/Reset

Individual channel status indicators (green, yellow, red)One System Solution
Honeywell Analytics’ one systemsolution to meet your safety
requirements

Relays, actuators, andaudio/visual alarms

XNX universal
transmitter

TouchpointTM Plus provides a reliablesafety solution for small-scale gas
detection systems across a wide range ofCloud

applications and industries. If you need tointegrate your gas detection with a higherlevel management system, the Modbus
output option makes this straightforward.
As the heart of your gas detection system,SD card

Sensepoint

Touchpoint Plus is designed to work with
Honeywell’s industry-leading gas detectors
and drive actuators, and audible and visual
alarms to provide a complete end-to-end
mV bridge
sensors

solution that you can configure as your own.
mA oopsensors
End userTYPICAL EXAMPLE OF A SMALLGAS DETECTION SYSTEM USINGTOUCHPOINT PLUSKey
Touchpoint
Plus ControlSystem
Touchpoint
Plus
ExpansionUnitGas
Detector
Audible &Visual AlarmDesigned for Speedand Reliability
Made of high-impact polymer plastic,
TouchpointTM Plus is versatileand durable. It is dustproof
and waterproof, and has beentested to withstand the toughest
operating environments, bothindoors and out. So you can counton the Touchpoint Plus to standup to the challenges of industrial
environments, from mechanicalrooms to chemical plants.
Touchpoint Plus is supplied withpre-drilled and sealed cable
entries and a unique tiered
internal arrangement providing
ease of access to save installers timeand money.

1. Main module
2. Input module

57

3. Relay output module

4

4. mA output module

6109831

5. Power supply
6. Display module
7. Touchscreen

2

8. Backup battery
9. Modbus TCP/Web
10. Modbus RTU

System Configuration Options
Not included in Expansion Unit

Provided As Standard

Alarm 1• Dedicated powered audiovisual
alarm drives• Common alarm outputs, one forfault and two configurable• Datalogging to SD card
• Remote reset and inhibit inputs

Alarm 2

Fault

VisibleFailure Configurable

Dedicated Audible/Visual Alarm OutputsSystem State Relays
12Outputs

Alarm 1Options• Choice of AC or DC supply voltage• Optional backup battery• Choice of inputs: 2, 4 , or 8 mA; 2, 4 , or8 mV; 2 mA and 2 mV; 4 mA and 4 mV
• Optional expansion unit for up to16 inputs• Choice of 12 or 24 relay outputs• Choice of 4 or 8 mA outputs• Optional RS485 Modbus RTU• Optional TCP/IP Modbus/HTTP

RemoteInhibitRemoteReset

Alarm 21

SD Card12Outputs

4-20mA

4-20mA

4Outputs

4Outputs

Alarm 300Fault

WarningInhibit000Input/Output
BuzzerMute/Reset
01 02 03 04 05 06 07 08
09 10 11 12 13 14 15 16Power Supply

110/220 VAC

Backup Battery

18-32 VDC

2, 4, or 8 Inputs
2-Wire 4-20 mA
3-Wire 4-20 mA
3-Wire mV Bridge

Installation
Quick and easy installation - designed to save
you time and money
TouchpointTM Plus can be directly wall-mounted, or, for an easier
1-man installation, simply use the optional mounting plate.
Open the hinged front cover to find plenty of space for wiring
and a unique tiered terminal arrangement for easy access.
Cable entries are pre-drilled and sealed ready to use reducing
installation time and cost further.

300mm

15 6 m m

Touchpoint Plus is supplied with 13 pre-drilled and sealed
cable entries for PG16/M20 glands.
Direct Surface Mounting
426mm

Optional Mounting Plate

2-Wire Loop Powered-VE

66 Ω0 Vdc

3-Wire Current Source

4-20mA

3-Wire Externally Powered

Simple devices, intrusive
configuration, power up
to 8 devices directly fromTouchpoint Plus

Searchpoint Optima Plus
Sensepoint XCD
Series 3000 MkII/MKIII
RAEGuard II PID
IAQPoint2
XNX Universal Transmitter
Searchline Excel
E3Point, EC F9, IR F966 Ω

0 Vdc

Sensepoint

705

SIG-VEAVAILABLE GAS DETECTORS

Signalpoint+24 Vdc

Enhanced devices, nonintrusive local operation,
in-field adjustment, power
up to 8 devices directlyfrom Touchpoint Plus

High-integrity devices,
specialized configuration,
in-field adjustment, monitor
up to 8 devices with external
power as required

Note: Other field devices available on request. Some devices are not available in all regions.

Sensitive
BeadSensor+VE

NonSensitive
Bead++VSignal

Signal_-V

3-Wire mV Bridge

Touchpoint Plus mV Input Module

66 Ω0 Vdc

SupplyTouchpoint Plus mA Input Module-VE

SIG+24 Vdc
External 24 VDCGNDSensor

4-20mA

4-20mA

+24 vdc

Touchpoint Plus mA Input Module

SIG+VE

SensorSensor+VE+24 vdc

Touchpoint Plus mA Input Module

Sensor Connection - Compatible with a wide range of field devices

GENERAL SPECIFICATION

Capacity

Input TypeGENERAL SPECIFICATION

Up to 8 channels with base unit, up to 16channels with expansion unit
2- or 3-wire, mA, mV, max. 15 W perchannel, max. 40 W total (with dedicated
A/V drive)/68 W total (without dedicated
A/V drive)

Available I/O Modules (continued)

Dual Input

Size (Wall-Mounted Version)

426 mm × 300 mm × 156 mm(16.8” x 11.8” x 6.1”)

Housing Material

Polycarbonate ABS

WeightMax. 8.5 kg (18.7 lb), max. 17 kg (37.4 lb)
with expansion unit

Relay Output

4-20mA Output

User Interface (UI) - Controller Only

Display

7’’ color LCD touchscreen. Graphic User Interface

Visual Indicators

3 LEDs for master indicators. LED for eachchannel. Green: Normal; Yellow: Fault:Inhibit; Red: Alarm

Audible Alarm≥ 70dB @ 1 m (3.28 ft)

ButtonCommon for reset/mute operation

Language

English, French, German, Italian, Dutch,Spanish, Portuguese, Russian, Chinese

AC Power

110/220 VAC, 50-60 Hz Manual switching

DC Power

18 to 32 VDC (+/-10%) Typical 24 VDC

Power Consumption

Max. 105 W (including detector and externaldevices), max. 210 W with expansion unit

Environmental-10 °C to +55 °C (14 °F to +131 °F)
continuous, up to 95% RH (noncondensing), IP65, and NEMA 4X
Instrument -25 °C to +60 °C (-13 °F to +140 °F), up to 95% RH (non-condensing)

Storage

Remote reset, remote inhibit

Common Outputs

4 powered A/V outputs for alarms and fault,
3 common alarm outputs

Electromagnetic
Compatibility andElectrical Safety

EMC/RFI (EN 50270:2015)
LVD (EN 61010-1:2010)
CSA-C22.2 No. 61010-1-04
UL 61010-1 (3rd Edition) and 508

Performance

EN 50271:2010; EN 60079-291:2007/2016; EN 45544-1 /-2/-3:2015;
EN 50104:2010 C22.2 No. 152-M1984,
ISA 12.13.01

Safety Integrity

IEC 61508:2010 Ed.2 SIL2, EN50271:2010

Hazardous Location

Class I, Division 2, Group A, B, C, and D,or non-hazardous onlyMarine

MED (Item No.: 3.54)

Others22.2 V Lithium Ion Battery, 2600 mAhcapacity (>30 minutes for typical system)
Configuration, logged events, and data
MODBUS TCP, WEB monitoring, andMODBUS RTU

Backup Battery
Datalogging

Available I/O Modules

4-20mA Input

Common Inputs

Approvals

Power Supply*

Operating

Catalytic-type flammable gas detectors(Honeywell models). 2-/4-/8-channel
modules, 10/12/16 with expansion unit
2-channel mA + 2-channel mV module or4-channel mA + 4-channel mV module
12 or 24 relay outputs, NO/C/NC
changeover, 1.7 A @ 30 VDC/250 VAC,
user-configurable - energized/de-energized,
latching/non-latching, time delay
4 or 8 isolated repeated mA outputs,
0-22 mA, 0-100% FSD = 4-20 mA

mV Input2- or 3-wire, 2/4/8 channel modules,
10/12/16 with expansion unit

Communication* Basic and expansion units each require a power supply** Not available in expansion unit

ORDERING INFORMATION

Output Option

Power
A: AC
D: DC

Product Name

4: 4ch mA Output
8: 8ch mA OutputN: No mA Output

Battery
B: Backup Battey
N: NoneMounting Type
W: Wall Mount

T PPLB AWA 8 S 8BNNN
Unit TypeInput Option

B: Base Unit
E: Expansion Unit

A2: 2ch mA Input
A4: 4ch mA Input
A8: 8ch mA Input
V2: 2ch mV Input
V4: 4ch mV Input
V8: 8ch mV Input
D4: 2ch mA + 2ch mV input
D8: 4ch mA + 4ch mV input

Communication**

R: MODBUS RTU
N: NoneRelay Option
S: 12 Relays
D: 24 Relays
N: No Relays

Future Use
Communication**
N: None
R: MODBUS TCP+WEB(read)
T: MODBUS TCPFor more informationwww.honeywellanalytics.com
www.raesystems.com

Europe, Middle East, Africa

Asia PacificAmericas

Technical Support

Life Safety Distribution GmbH
Tel: 00800 333 222 44 (Freephone number)
Tel: +41 44 943 4380 (Alternative number)
Middle East Tel: +971 4 450 5800 (Fixed Gas Detection)
Middle East Tel: +971 4 450 5852 (Portable Gas Detection)

Honeywell Analytics Distribution Inc.
Tel: +1 847 955 8200
Toll free: +1 800 538 0363
RAE Systems by Honeywell
Phone: 408 952 8200
Toll free: 1 888 723 4800

Honeywell Industrial Safety
Tel: +82 (0) 2 6909 0300
India Tel: +91 124 4752700
China Tel: +86 10 5885 8788 3000
analytics.ap@honeywell.com

EMEA: HAexpert@honeywell.com
US: ha.us.service@honeywell.com
AP: ha.ap.service@honeywell.com

Please Note:
While every effort has been made to ensure accuracy in this publication, no responsibility
can be accepted for errors or omissions. Data may change, as well as legislation, and you
are strongly advised to obtain copies of the most recently issued regulations, standards,and guidelines. This publication is not intended to form the basis of a contract.
Touchpoint Plus Datasheet | Rev 4 | 02/19© 2019 Honeywell International Inc.