§ PLUG-IN TRANSDUCER § 1 OUTPUT TYPE

SIGNAL TRANSDUCERULTRAHIGH SPEED ISOLATOR
HSTP1 -

■ Use
Amplifies various kinds of DC signals and converts them into a unified
intersystem signal at an ultrahigh speed. Because the device is highspeed response (≦500μs/90%), it can be used for insulating a feedback
signal of a control circuit and so on.

■ Features
1. With built-in ultrahigh speed isolator.
2. Constant voltage/current output.
3. Withstand voltage between input, output, auxiliary supply and outercase (earth) is AC1, 500V (50/60Hz), complete insulation for 1 minute.
4. Impulse withstands voltage 5kV, 1.2/50µs (between electric circuit andouter case), and positive/negative polarity 3 times each is guaranteed.
5. With output line surge protection. (2, 000A, ±8/20µs, positive/negativepolarity)

HSTP1-C7F1(80×50×121mm/400g)■ Specification
Input (input resistance or voltage drop)
A1 : DC0-10mV (approx.1MΩ)
A2 : DC0-50mV (approx.1MΩ)
A3 : DC0-60mV (approx.1MΩ)
A4 : DC0-100mV (approx.1MΩ)
A5 : DC0-1V (approx.1MΩ)
A6 : DC0-5V (approx.1MΩ)
A7 : DC0-10V (approx.1MΩ)
A8 : DC1-5V (approx.1MΩ)
B1 : DC±10mV (approx.1MΩ)B2 : DC±50mV (approx.1MΩ)B3 : DC±60mV (approx.1MΩ)
B4 : DC±100mV (approx.1MΩ)B5 : DC±1V (approx.1MΩ)
B6 : DC±5V (approx.1MΩ)

Output (load resistance)

Auxiliary supply

Common specification

C1 : DC0-10μA (100mV) *1

1 : DC0-100mV (≧200Ω)

1 : AC100V±10%,Tolerance: ±0.25% *2

C2 : DC0-100μA (100mV)

2 : DC0-1V (≧200Ω)

50/60HzC3 : DC0-1mA (approx.100Ω)

3 : DC0-5V (≧1kΩ)

2 : AC110V±10%,

C4 : DC0-5mA (approx.100Ω)

4 : DC 0-10V (≧2kΩ)50/60HzC5 : DC0-10mA (approx.100Ω)

5 : DC1-5V (≧1kΩ)

3 : AC200V±10%,

AC power source:3VA

C6 : DC0-16mA (approx.100Ω)

6 : DC±5V (≧1kΩ)50/60HzDC power source:4W

C7 : DC4-20mA (approx.100Ω)

7 : DC±10V (≧2kΩ)

4 : AC220V±10%,

D1 : DC±10μA (±100mV)*1A : DC0-1mA (≦10kΩ)

50/60HzAC power source:400g

D2 : DC±100μA (±100mV)

B : DC0-5mA (≦2kΩ)

5 : DC24V±10%

DC power source:300g

D3 : DC±500μA (±100mV)C : DC0-10mA (≦1kΩ)

6 : DC48V±10%

D4 : DC±1mA (approx.100Ω)

D : DC0-16mA (≦600Ω)

0 : other thanD5 : DC±5mA (approx.100Ω)

E : DC1-5mA (≦3kΩ)D6 : DC±10mA (approx.100Ω)

F : DC4-20mA (≦750Ω)

00 : other than those above

0 : other than those above

Response time:
500μs/90%
Consumption VA:

Weight:those above

B7 : DC±10V (approx.1MΩ)*1. Circuit voltage ≦15V for an input of 10μA.
*2. Tolerance becomes ±0.5% when input voltage is less than 50mV; input current is less than 100μA.
● Open of current output: even if the current output terminal is used in a state of regular open, there is no problem. Also, a voltage of approx. 25V
occurs on the output terminal.

● Option: surge absorber (5kV, 1.2/50µs positive/negative polarity)
When an inductive lightning surge occurs from input or output side, this device absorbs the surge and protects
connected equipments.
However, the device is not necessary if the connected equipment is protected by an arrester or suchlike.
● Ultrahigh speed response
Keep in mind that because this device is high speed response, its ripple-removal ability is not as high as those ofother models.
● UR-1 precise resistance unit (selling separately)
Please use a UR-1 combined with an ultrahigh speed isolator of voltage input. When changing the ultrahigh speed
isolator in a hot line state at the time of current input, if measures against open are necessary, connect UR-1 tosocket and convert it into a voltage signal before using it. (UR-1, the resistance specified)

Products List3

§ PLUG-IN TRANSDUCER § 1 OUTPUT TYPE

SIGNAL TRANSDUCER■ Connection diagram

Indicated in ( ) are the polarities in the case of DC auxiliary supply.

■ Block diagram①Low-drift amplifying circuit②Output circuit③④

Output line surge protection circuit
Insulated power source circuit■ Purchase specifications
TypeHSTP1-C 7InputF1Output
AuxiliarySSurge absorber (option)

supplyProducts List4