54321Nonhazardous Locations

Hazardous (Classified) Location
Class I / Division 1, 2 / Groups ABCDClass I, Zone 0, IIC
Class II / Division 1, 2 / Groups EFG
Class III

Installation Notes RID14
Temperature range
T4T5-40°C ... +70°C

T6-40°C ... +55°C

Power supply

See also installation notes
for using power supply

B

PROFIBUS®/
FOUNDATION FieldbusTM

NONINCENDIVEB

EXPLOSION PROOF
Class I / Div. 1 / Groups ABCD
DUST IGNITION PROOF
Class II, III / Div. 1 / Groups EFG- CSA approved apparatus must be installed in accordance with manufacturer’s instructions.
- Installation must be in accordance with Canadian Electrical Code.
- All Conduits must be assembled with a minimum of five full threads engagement.
- Field indicator must be CSA approved for appropriate area classification.
- Use supply wires suitable for 5°C above surroundings.
- Seal all conduits within 18 inches of enclosure.
- In Class II use a dust tight seal.
- A dust tight seal must be used for conduit entry when the field indicator is used in a Class II or Class IIIlocation.
- Keep tight when circuits alive.
- Supply circuit (Terminals + and -)U£ 35 V DC
P=3W
- Warning: Substitution of components may impair suitability for Class I, Division 2.
- Warning: Do not disconnect equipment unless power has been switched off or the area is known to be
non hazardous.

AA+-40°C ... +80°C

Class I / Zone 2 / Ex nA IIC
Class I / Div. 2 / Groups ABCD

Nonhazardous Locations

Hazardous (Classified) Location
Class I / Division 2 / Groups ABCDClass I, Zone 2, IIC

CSA approved Associated Apparatus
suitable for entity or FNICO concept
or Associated Nonincendive FieldWiring ApparatusC+
See also installation notes
for using power supplyC- Intrinsic safety barrier is not required. Vmax £ 35 V DC.
- Warning: Do not disconnect equipment unless power has been switched off or the area is known to be nonhazardous.
- Nonincendive field wiring installation
The Nonincendive Field Wiring Circuit Concept allows interconnection of Nonincendive Field Wiring
Apparatus with Associated Nonincendive Field Wiring Apparatus or Associated Intrinsically Safe Apparatus or
Associated Apparatus not specifically examined in combination as a system using any of the wiring methods
permitted for unclassified locations, when Voc £ Vmax, Ca ³ Ci + Ccable, La ³ Li + Lcable.
Field indicator Nonincendive Field Wiring parameters are as follows:
Ui or Vmax
£ 35 V DC Ci = £ 5 nF
Li £ 10 µF
For these current controlled circuits, the parameter Imax is not required and need not to be aligned withparameter Isc and It of the Associated Nonincendive Field Wiring Apparatus or Associated Apparatus.
- Warning: Explosion Hazard- Do not disconnect equipment unless power has been switched off or the area isknown to be non-hazardous- The field indicator is suitable to be installed according the FNICO concept.
NOTE
When the product is installed as a FNICO installation use drawing 12 08 00 112.

Pfanzelt
Volume (mm³)

DesignedPfanzelt
Refer to protection notice
ISO 16016

Drawing No.

Date (yyyy-mm-dd)

12 08 00 114

2009-07-06
Date (yyyy-mm-dd)

Unit

2009-07-05

Edge of working parts Geometrical tolerancing
ISO 2768-mH-E
ISO 13715

Part No.

RID14

Dwg.rev.

-Scale1:1
Format

A4

Revision no.

-71540276

Revision date (yyyy-mm-dd)

Name

Material--

XA02302R/09/EN/01.20

Title

CONTROL DRAWING CSA
XP/NI/DIPD

D

Approved

SeriesObjekt version

Sheet

Endress + Hause r
WetzerNesselwang / Germany

1 of 1 GmbH+Co. KG

54321