PTB 00 ATEX 2129 X
Device with II 2G/D EX m / II 2G/D EX em approval
Geräte mit II 2G/D EX m / II 2G/D EX em Zulassung
Appareils avec mode de protection II 2G/D EX m / II 2G/D EX em

Example / Beispiel / Exemple
Type 6013

Operating Instructions
Bedienungsanleitung
Manuel d‘utilisation

We reserve the right to make technical changes without notice.
Technische Änderungen vorbehalten.
Sous réserve de modifications techniques.
© Bürkert Werke GmbH & Co. KG, 200 - 2017
Operating Instructions 1706/1_EU-EN_0080 / Original DE

PTB 00 ATEX 2129 X
Contents﻿
1. OPERATING INSTRUCTIONS....................................................................4
1.1. Symbols............................................................................................... 4
2. AUTHORIZED USE..........................................................................................5
2.1. Restrictions......................................................................................... 5
2.2. EX approval........................................................................................ 5
3. BASIC SAFETY INSTRUCTIONS..............................................................6
4. GENERAL INFORMATION............................................................................7
4.1. Contact addresses........................................................................... 7
4.2. Warranty.............................................................................................. 7
4.3. Information on the Internet.............................................................. 7
5. APPLICATION CONDITIONS OF THE DEVICES..............................7
5.1. Short-circuit protection.................................................................... 7
5.2. Operation only with associated valve........................................... 8
5.3. Individual assembly........................................................................... 8
5.4. Operating temperature range......................................................... 8
5.5. Ambient temperature > 55 °C....................................................... 8
5.6. Application in petrol pumps............................................................ 8
5.7. Model with a terminal box................................................................ 9

7. ASSEMBLY........................................................................................................ 13
7.1. Safety instructions..........................................................................137.2. Installation of Type 6013...............................................................14
8. START-UP.......................................................................................................... 14
8.1. Safety instructions..........................................................................148.2. Start-up.............................................................................................14
9. MAINTENANCE, TROUBLESHOOTING............................................. 15
9.1. Safety instructions..........................................................................15
9.2. Maintenance work...........................................................................15
9.3. Troubleshooting...............................................................................15
10. ACCESSORIES............................................................................................ 16
10.1. Safety instructions........................................................................16
11. TRANSPORT, STORAGE, DISPOSAL............................................... 16

6. TECHNICAL DATA......................................................................................... 10
6.1. Conformity........................................................................................10
6.2. Standards..........................................................................................10
6.3. Licences............................................................................................10
6.4. Operating conditions......................................................................10
6.5. Electrical data..................................................................................11

english3

PTB 00 ATEX 2129 X
Operating instructions

1.

OPERATING INSTRUCTIONSCAUTION!

The operating instructions describe the entire life cycle of the device.
Keep these instructions in a location which is easily accessible toevery user and make these instructions available to every new ownerof the device.

Warns of a possible danger!
• Failure to observe this warning may result in a medium or minor
injury.

The operating instructions contain important safety
information!

NOTE!

Failure to observe these instructions may result in hazardous
situations.
• The operating instructions must be read and understood.

Warns of damage to property!
• Failure to observe the warning may result in damage to thedevice or the equipment.

Indicates important additional information, tips andrecommendations.

1.1.

Symbols
DANGER!

Warns of an immediate danger!
• Failure to observe the warning may result in a fatal or serious
injury.
WARNING!
Warns of a potentially dangerous situation!
• Failure to observe the warning may result in serious injuries ordeath.

4

englishRefers to information in these operating instructions or inother documentation.

→→designates a procedure which you must carry out.

PTB 00 ATEX 2129 X
Authorized use

2.

AUTHORIZED USE

Unauthorized use of the device Type 6013 may be dangerous
to people, nearby equipment and the environment.
• The device is used is used exclusively as a solenoid valve for media
permitted according to the data sheet and for use in Explosion
group II, Category 2G or 2D and Temperature class T4, T5 or T6(see specifications on theapproval plate).
• The device may be used only for the applications designated inchapter “5. Application conditions of the devices” and in conjunction with third-party devices and components recommended andauthorized by Bürkert.
• The applied protection class is encapsulation EX “m” for coils withcable connection or encapsulation with increased safety EX “em”
for coils with terminal box.
• Observe the requirements of EN 61241-0/-1 e.g. with reference
to dust deposits and temperatures.
• The solenoid coil AC10 is used to activate valves which control
the gaseous or liquid media. The device is part of a closed system and may also be used in gasoline pumps to control gasoline
as Category 2.
• The faultless and reliable operation of the system assumes correct transportation, correct storage and installation as well as
careful operation and maintenance. Any other use is regarded as
unauthorized. Bürkert is not liable for any resulting damage. The
user alone bears the risk.
• Only use the device for its intended purpose.

2.1.

Restrictions

If exporting the system/device, observe any existing restrictions.

2.2.

EX approval

The EX approval is only valid if the modules and components authorized by Bürkert are used as described in these operating instructions.
Type 0742 may be used only in combination with the additional components released by Bürkert, otherwise the EX approval will be voided!
If any unauthorized changes are made to the device, modules or components, the EX approval will also be voided.

english5

PTB 00 ATEX 2129 X
Basic safety instructions

3.

BASIC SAFETY
INSTRUCTIONS

These safety instructions do not make allowance for any• Contingencies and events which may arise during the installation,
operation and maintenance of the devices.
• Local safety regulations – the operator is responsible for observing
these regulations, also with reference to the installation personnel.

Danger of explosion caused by electrostatic charge!
If there is a sudden discharge from electrostatically charged
devices or persons, there is a danger of explosion in the EX area.
• Using suitable measures, ensure that no electrostatic charges
can occur in the EX area.
• Clean the device surface by gently wiping it with a damp or antistatic cloth only.
General Hazardous Situations.

Danger of explosion!
• The device is part of a closed system and must not be removed
during operation.
Risk of electric shock!
Acute risk of injury from hazardous body voltage! Risk of damaging
the device by short-circuit!
• Before reaching into the device or the equipment, switch off thepower supply and secure to prevent reactivation!
• Observe applicable accident prevention and safety regulations
for electrical equipment!
Danger – high pressure!
When reaching into the system, there is an acute risk of injury.
• Before dismounting pneumatic lines and valves, turn off thepressure and vent the lines.
• During the installation, make certain the flow direction is correct.
• Observe applicable accident prevention and safety regulations
for pressurized devices.
6

englishTo prevent injuries:• Ensure that the system cannot be activated unintentionally.
• Installation and maintenance work may be carried out only byauthorized technicians with the appropriate tools.
• After an interruption in the power supply or pneumatic supply,
ensure that the process is restarted in a defined or controlledmanner.
• The device may be operated only when in perfect condition andin consideration of the operating instructions.
• The general rules of technology must be observed for application
planning and operation of the device.
Failure to observe this operating manual and its operating
instructions as well as unauthorized tampering with the device
release us from any liability and also invalidate the warranty
covering the devices and accessories!

PTB 00 ATEX 2129 X
General information

4.

GENERAL INFORMATION

4.1.

Contact addresses

Germany
Bürkert Fluid Control Systems
Sales Center
Christian-Bürkert-Str. 13-17
D-74653 IngelfingenTel.  + 49 (0) 7940 - 10 91 111
Fax  + 49 (0) 7940 - 10 91 448
E-mail: info@de.buerkert.com
International
Contact addresses can be found on the final pages of the printed
operating instructions.
And also on the Internet at: www.burkert.com

4.2.

Warranty

5.

APPLICATION CONDITIONS OF
THE DEVICES

5.1.

Short-circuit protection

To protect against short-circuits, either a fuse (max. 3 x Ib in accordancewith IEC 60127-2-1) must be connected upstream of each magnet
according to the rated current of the magnet, or a motor protection
switch with short-circuit and thermal quick release (set to rated current).
If rated currents of the magnet are very low, the fuse with the lowest
current value is adequate in accordance with the stated IEC standard.
This fuse may be housed in the associated supply unit or must beconnected separately upstream. The rated voltage of the fuse must be
equal to or greater than the indicated nominal voltage of the magnet.
The breaking capacity of the fuse insert must be equal to or greaterthan the maximum short-circuit current accepted at the installation
location (usually 1500 A).
The nominal fuse value is indicatedon the magnet.

The warranty is only valid if the device is used as intended in accordancewith the specified application conditions.

4.3.

Information on the Internet

The operating instructions and data sheets for Type 6013 can be foundon the Internet at: www.burkert.com

Fuse
0,08 A

english7

PTB 00 ATEX 2129 X
Application conditions of the devices

5.2.

Operation only with associatedvalve

The solenoid coils type AC10 - PD73 to AC10 - PD86 may be operated
as a complete device only with associated valve body which satisfies thefollowing requirements:• Materials for individual and block assembly:
Metal (brass, aluminum, stainless steel) or plastic (e.g. polyamide
PA 6 GV).
DANGER!
Danger of explosion!
• If devices are used in gasoline pumps to control gasoline as
Category 2, a valve body made of metal (brass, aluminum or stainless steel) must be used.
Minimum dimensions of the valve bodies:• 32 mm x 32 mm x 10 mm (L x B x H)
A larger valve body with better heat conductivity may be attachedat any time.

5.3.

Individual assembly

The solenoid coils type AC10 - PD47 to AC - PD72 are suitable forindividual assembly only.

5.4.

Operating temperature range

For each type observe the operating temperature range specified in
the Electrical Data.
8

english

5.5.

Ambient temperature > 55 °C

In the case of solenoid coils type AC10 - 6 - PD53 and AC10 - 6 PD66 for an ambient temperature > 55 °C a heat-resistant cable is
used.

5.6.

Application in petrol pumps
DANGER!

Risk of explosion by opening the device!
• The device is a closed system. It must not be removed!
Danger of explosion!
• If devices are used in gasoline pumps to control gasoline as
Category 2, a valve body made of metal (brass, aluminum or
stainless steel) must be used.
The solenoid coils type AC10 may also be used to control gasoline
in Category 2 if there is no air and no oxygen in the closed system.
This also applies to starting and switching off the system.
• The coil is mounted on the core guide pipe.
• The valves always represent a closed system.
The solenoid coils may be removed by the manufacturer
only!

PTB 00 ATEX 2129 X
Application conditions of the devices

5.7.

Model with a terminal box
DANGER!

Coil AC10

Danger of explosion!
• Only specified cables and lines may be used.
• The operator must ensure an adequate strain relief.
• Lines with an outer diameter from 6 mm to 13 mm may be used.
Observe the maximum thermal load of the installed cables and lines.
• The inserted seal must be adjusted to the diameter of the cable /line.
• The rated cross-section of the cables / line cores must be at least
0.75 mm² and must not exceed 2.5 mm².
• Screws for attaching the cover of the terminal box must be tightened to a torque of 100 Ncm (± 5 %).
• The terminals must be tightened to a torque of 1–1.5 Nm.

Device socket withcable

Temperature conditions at 60 °C.
Ambient temperature on the solenoid coil AC10
Temperature class

Coil size

Absolute temperature [°C]

T4

5

118

6

113

4

93

5

87

6

90

5

79

6

75

T5

T6

The solenoid coils can be designed with a terminal box.
The attachment of a terminal box changes the ignition protection typeof these solenoid coils.
Identification with attached terminal box:
II 2G/D EX em II T4, T5, T6

english9

PTB 00 ATEX 2129 X
Technical data

6.

TECHNICAL DATA

6.1.

Conformity

Operating conditions
WARNING!

The device conforms to the EC directives according to the EC
Declaration of Conformity.

6.2.

6.4.

Standards

Danger of explosion!
It is highly risky to exceed the technical data indicated on therating plate!
• Never exceed the technical data indicated on the rating plate.

The conformity with EC guidelines is guaranteed in accordance withstandards:• EN 60079-0, EN 60079-7, EN 60079-18, EN 61241-0,
EN 61241-1, EN 13463-1

6.3.

CE identification

Licences

PTB approval number

The EC type-examination certificate PTB 00 ATEX 2129 X wasissued by the
PTB (Physikalisch Technische Bundesanstalt)
Bundesallee 100
38116 Braunschweig

Rating plateFuse
0,08 A

which also audits production (CE 102).
The EC type-examination certificate can be found on the Internet at:
www.burkert.com

10

englishFig. 1:

Location of the rating plate

PTB 00 ATEX 2129 X
Technical data

6.4.1.

Rating plate
IEC EX - Approval number
Protection class / Temperature class

D-74653 Ingelfingen

EX - CodeII2 G Ex em II T4/T5/T6
II2 D IP65 T=135°C
IEC Ex PTB 07.0021X
AC10-Z3-5 24V ~ 7W
S/N XXXXXXXXXXXX

W22LS

Identification number of the coil
Serial number of the coil
Coil type, Voltage, Power

Fig. 2:

Description of the rating plate

6.5.

Electrical data

6.5.1.

Coils for individual assembly

Universal current, nominal voltage 12 ... 400 V, frequency 0 ... 60 Hz
Coil type

Rated current
[A]

Power
limit
[W]

Max. permitted
ambient temperature [°C]

Temperatureclass

AC10-5-PD47

0.68 ... 0.02

7-30 ... +60

T4

AC10-5-PD48

0.33 ... 0.01

4-30 ... +50

T5

AC10-5-PD49

0.25 ... 0.007

3-30 ... +60

T5

AC10-5-PD50

0.25 ... 0.007

3-30 ... +40

T6

AC10-5-PD51

0.19 ... 0.005

2.25-30 ... +50

T6

AC10-5-PD52

0.114 ... 0.003

1.25-30 ... +60

T6

AC10-6-PD53

0.8 ... 0.02

9-30 ... +60

T4

AC10-6-PD54

0.31 ... 0.009

3.5-30 ... +60

T5

AC10-6-PD55

0.16 ... 0.005

1.8-30 ... +60

T6

AC10-4-PD56

0.35 ... 0.01

4-30 ... +50

T5

AC10-4-PD57

0.25 ... 0.007

3-30 ... +60

T5

AC10-4-PD59

0.13 ... 0.003

1.5-30 ... +60

T6

AC10-5-PD60

0.68 ... 0.02

7-40 ... +60

T4

AC10-5-PD61

0.33 ... 0.01

4-40 ... +50

T5

AC10-5-PD62

0.25 ... 0.007

3-40 ... +60

T5

AC10-5-PD63

0.25 ... 0.007

3-40 ... +40

T6english11

PTB 00 ATEX 2129 X
Technical data

AC10-5-PD64

0.19 ... 0.005

2.25-40 ... +50

T6

AC10-5-PD65

0.114 ... 0.003

1.25-40 ... +60

T6

AC10-6-PD66

0.8 ... 0.02

9-40 ... +60

T4

AC10-6-PD67

0.31 ... 0.009

3.5-40 ... +60

T5

AC10-6-PD68

0.16 ... 0.005

1.8-40 ... +60

T6

AC10-4-PD69

0.35 ... 0.01

4-40 ... +50

AC10-4-PD70

0.25 ... 0.007

3-40 ... +60

AC10-4-PD72

0.13 ... 0.003

1.5-40 ... +60

6.5.2.

Universal current, nominal voltage 12 ... 400 V, frequency 0 ... 60 Hz
Coil type

Rated current
[A]

Power
limit
[W]

Max. permitted
ambient
temperature[°C]

Temperature
class

1)

T5

AC10-5-PD73

0.68 ... 0.02

7-30 ... +40

T4

1

T5

AC10-5-PD74

0.25 ... 0.007

3-30 ... +50

T5

1

T6

AC10-5-PD75

0.19 ... 0.005

2.25-30 ... +40

T6

1

AC10-5-PD76

0.114 ... 0.003

1.25-30 ... +60

T6

1

AC10-4-PD77

0.33 ... 0.01

4-30 ... +40

T5

5

AC10-4-PD78

0.25 ... 0.007

3-30 ... +50

T6

5

AC10-4-PD79

0.13 ... 0.003

1.5-30 ... +55

T6

5

AC10-5-PD80

0.68 ... 0.02

7-40 ... +40

T4

1

AC10-5-PD81

0.25 ... 0.007

3-40 ... +50

T5

1

AC10-5-PD82

0.19 ... 0.005

2.25-40 ... +40

T6

1

AC10-5-PD83

0.114 ... 0.003

1.25-40 ... +60

T6

1

AC10-4-PD84

0.33 ... 0.01

4-40 ... +40

T5

5

AC10-4-PD85

0.25 ... 0.007

3-40 ... +50

T5

5

AC10-4-PD86

0.13 ... 0.003

1.5-40 ... +55

T6

5

Coils for individual or battery
assembly

DANGER!
Risk of explosion due to overheating!
In the case of battery assembly observe the following data of thevalves:• Dimension of the valve body: 32 mm x 32 mm x 10 mm.
• Material of the valve body: Brass (MS), aluminium (AL), stainlesssteel (VA) or plastic (PA 6 GV).

1)12englishIn the case of battery assembly: min. distance from the wall [mm]PTB 00 ATEX 2129 X
Assembly

7.

ASSEMBLY

7.1.

Safety instructions
DANGER!

Danger of explosion!
The device is a closed system. It must not be removed.
The following safety instructions must be observed:• The surface of the device may become electrostatically charged.
In potentially explosive areas the surface of the devices may becleaned with a damp or an anti-static cloth only.
• Only specified cables and lines may be used.
• The operator must ensure an adequate strain relief.
• Lines with an outer diameter of 6 mm - 13 mm can be used.
Observe the maximum thermal load of the installed cables andlines.
• The inserted seal must be adjusted to the diameter of the cable/ line.
The rated cross-section of the cables / line cores must be atleast 0.75 mm² and must not exceed 2.5 mm².
• Screws for attaching the cover of the terminal box must be
tightened to a torque of 100 Ncm (± 5 %).

DANGER!
Risk of electric shock!
Acute risk of injury from hazardous body voltage! Risk of damaging
the device by short-circuit!
• Before reaching into the device or the equipment, switch off thepower supply and secure to prevent reactivation!
• Live terminals in the terminal box may cause an electric shock,short-circuit or explosion. Switch off the power supply. Only thenopen the terminal box.
• The connection lines of the electromagnets must be permanently
installed in such a way that they are adequately protected frommechanical damage.
• Observe applicable accident prevention and safety regulations
for electrical equipment!
Risk of explosion due to overheating!
In the case of battery assembly observe the following data of the valves:• Dimension of the valve body: 32 mm x 32 mm x 10 mm.
• Material of the valve body: Brass (MS), aluminium (AL), stainlesssteel (VA) or plastic (PA 6 GV).
WARNING!
Danger – high pressure!
When reaching into the system, there is an acute risk of injury.
• Before dismounting pneumatic lines and valves, turn off the pressure and vent the lines.
• During the installation, make certain the flow direction is correct.
• Observe applicable accident prevention and safety regulations
for pressurized devices.

english13

PTB 00 ATEX 2129 X
Start-up

7.2.

Installation of Type 6013
Any installation position.
Preferably with magnet system face up.

START-UP

8.1.

Safety instructions
WARNING!

1. Clean pipelines.
2. Any installation position

Risk of injury from improper operation!

→→Preferential direction with actuator face up.
3. Connect dirt trap upstream→→Observe direction of flow!
4. Seal→→PTFE.
5. Screw in pipelines→→Observe direction of flow!
6. Install / remove.

Improper operation may result in injuries as well as damage to thedevice and the area around it.
• Before start-up, ensure that the operating personnel are familiar
with and completely understand the contents of the operating
instructions.
• Observe the safety instructions and intended use.
• Only adequately trained personnel may start up the equipment/
the device.

8.2.

NOTE!
Information for devices with connecting cable:
Connecting cable and coil are encapsulated. They must not be
removed!
Always connect protective conductor!

7. Connect to power supply.

14

8.

englishStart-up

Before starting up the device, ensure that:• the device has been installed correctly,• the connection has been made properly,• the device is not damaged,• all screws have been tightened.

PTB 00 ATEX 2129 X
Maintenance, Troubleshooting

9.
9.1.

MAINTENANCE,TROUBLESHOOTING
Safety instructions
WARNING!

9.2.

Maintenance work

The devices are maintenance-free when operated under the conditions described in this manual.

9.3.

Troubleshooting

If malfunctions occur, ensure that:

Danger of explosion caused by electrostatic charge!

• the device has been installed correctly,

If there is a sudden discharge from electrostatically charged
devices or persons, there is a danger of explosion in the EX area.
• Using suitable measures, ensure that no electrostatic charges
can occur in the EX area.
• Clean the device surface by gently wiping it with a damp or antistatic cloth only.

• the connection has been made properly,• the device is not damaged,• all screws have been tightened,• the voltage and pressure have been switched on,• the pipelines are free.

Risk of injury from improper servicing, repairs andmaintenance!
• The device may be serviced and maintained by authorized technicians only and with the appropriate tools!
• The unit may be repaired by the manufacturer only!
• When repairing or servicing the system, the valve must not be
opened and the protective conductor connection must not be
disconnected!

english15

PTB 00 ATEX 2129 X
Accessories

10.

ACCESSORIES

11.

10.1.

Safety instructionsNOTE!

CAUTION!

Transport damages!

Risk of injury and/or damage by the use of incorrect parts!
Incorrect accessories and unsuitable spare parts may cause injuries
and damage the device and the surrounding area.
• Use only original accessories and original spare parts from Bürkert.
If the devices are designed with a terminal box, the fuse of type 1058
with approval PTB 01 ATEX 2064 U can be used in temperatureclass T4.
Fuse Type
1058

Order
number

Fuse Type
1058

Order
number

0.063 A

153 7170.500 A

153 7350.080 A

153 7450.630 A

153 7360.100 A

153 7180.800 A

153 7370.125 A

153 719

1.000 A

153 738

0.160 A

153 720

1.250 A

153 7390.200 A

153 7311.600 A

153 7460.315 A

153 733

2.000 A

153 7400.400 A

153 734

3.150 A

153 742

16

TRANSPORT, STORAGE,DISPOSAL

englishInadequately protected equipment may be damaged duringtransport.
• During transportation protect the device against wet and dirt inshock-resistant packaging.
• Avoid exceeding or dropping below the allowable storage
temperature.
Incorrect storage may damage the device.
• Store the device in a dry and dust-free location!
• Storage temperature: -40 … +55 °C.
Damage to the environment caused by device components
contaminated with media.
• Ensure the device and packaging are disposed of in an environmentally sound manner.
• Observe applicable regulations relating to refuse disposal andthe environment.

PTB 00 ATEX 2129 X
Inhaltsverzeichnis﻿
1. DIE BEDIENUNGSANLEITUNG............................................................. 18
1.1. Darstellungsmittel............................................................................18
2. BESTIMMUNGSGEMÄSSE VERWENDUNG1����������������������������������� 19
2.1. Beschränkungen.............................................................................192.2. EX Zulassung...................................................................................19
3. GRUNDLEGENDE SICHERHEITSHINWEISE.................................. 20
4. ALLGEMEINE HINWEISE........................................................................... 21
4.1. Kontaktadresse................................................................................21
4.2. Gewährleistung...............................................................................21
4.3. Informationen im Internet...............................................................21
5. EINSATZBEDINGUNGEN DER GERÄTE........................................... 21
5.1. Kurzschlussschutz...........................................................................215.2. Betrieb nur mit zugehörigem Ventil.............................................225.3. Einzelmontage..................................................................................225.4. Einsatztemperaturbereich..............................................................225.5. Umgebungstemperatur > 55 °C.................................................225.6. Einsatz in Tanksäulen.....................................................................225.7. Ausführung mit einem Klemmenkasten......................................23

7. MONTAGE......................................................................................................... 27
7.1. Sicherheitshinweise........................................................................27
7.2. Montage des Typs 6013...............................................................28
8. INBETRIEBNAHME....................................................................................... 28
8.1. Sicherheitshinweise........................................................................28
8.2. Inbetriebnahme................................................................................28
9. WARTUNG, FEHLERBEHEBUNG.......................................................... 29
9.1. Sicherheitshinweise........................................................................29
9.2. Wartungsarbeiten............................................................................29
9.3. Fehlerbehebung...............................................................................29
10. ZUBEHÖR....................................................................................................... 30
10.1. Sicherheitshinweise.....................................................................30
11. TRANSPORT, LAGERUNG, VERPACKUNG................................... 30

6. TECHNISCHE DATEN................................................................................. 24
6.1. Konformität........................................................................................24
6.2. Normen..............................................................................................24
6.3. Zulassungen.....................................................................................24
6.4. Betriebsbedingungen.....................................................................24
6.5. Elektrische Daten............................................................................25

deutsch17

PTB 00 ATEX 2129 X
Die Bedienungsanleitung1.

DIE BEDIENUNGSANLEITUNGVORSICHT!

Die Bedienungsanleitung beschreibt den gesamten Lebenszyklus
des Gerätes. Bewahren Sie diese Anleitung so auf, dass sie für jeden
Benutzer gut zugänglich ist und jedem neuen Eigentümer des Gerätes
wieder zur Verfügung steht.

Warnt vor einer möglichen Gefährdung!
• Nichtbeachtung kann mittelschwere oder leichte Verletzungen
zur Folge haben.

Die Bedienungsanleitung enthält wichtige Informationen zur
Sicherheit!

HINWEIS!

Das Nichtbeachten dieser Hinweise kann zu gefährlichen Situationen
führen.
• Die Bedienungsanleitung muss gelesen und verstanden werden.

Warnt vor Sachschäden!
• Bei Nichtbeachtung kann das Gerät oder die Anlage beschädigt
werden.

Bezeichnet wichtige Zusatzinformationen, Tipps und
Empfehlungen.

1.1.

Darstellungsmittel
GEFAHR!

Warnt vor einer unmittelbaren Gefahr!
• Bei Nichtbeachtung sind Tod oder schwere Verletzungen die
Folge.
WARNUNG!
Warnt vor einer möglicherweise gefährlichen Situation!
• Bei Nichtbeachtung drohen schwere Verletzungen oder Tod.

18

deutschVerweist auf Informationen in dieser Bedienungsanleitungoder in anderen Dokumentationen.

→→markiert einen Arbeitsschritt, den Sie ausführen müssen.

PTB 00 ATEX 2129 X
Bestimmungsgemäße Verwendung

2.

BESTIMMUNGSGEMÄSSE
VERWENDUNG

Bei nicht bestimmungsgemäßem Einsatz des Gerätes Typ 6013
können Gefahren für Personen, Anlagen in der Umgebung unddie Umwelt entstehen.
• Das Gerät dient ausschließlich als Magnetventil für die laut Datenblatt zulässigen Medien und für den Einsatz in Explosionsgruppe
II, Kategorie 2G bzw. 2D und Temperaturklasse T4, T5 oder T6(siehe Angaben auf dem
Zulassungsschild).
• Das Gerät darf nur für die im Kapitel „5. Einsatzbedingungender Geräte“ vorgesehenen Einsatzfälle und in Verbindung mit
von Bürkert empfohlenen bzw. zugelassenen Fremdgeräten und-komponenten verwendet werden.
• Die angewandte Schutzart ist die Vergusskapselung EX „m“ fürSpulen mit Kabelanschluss oder die Vergusskapselung mit erhöhter Sicherheit EX „em“ für Spulen mit Klemmenkasten.
• Die Anforderungen der EN 61241-0/-1 z. B. in Bezug auf Staubablagerungen und Temperaturen einhalten.
• Die Magnetspule AC10 dient zum Betätigen von Ventilen, diegasförmige oder flüssige Medien steuern. Das Gerät ist Teil einesgeschlossenen Systems und darf auch in Tanksäulen zur Steuerung von Benzin als Kategorie 2 eingesetzt werden.
• Der einwandfreie und sichere Betrieb des Systems setzt
sachgemäßen Transport, sachgemäße Lagerung und Installation sowie sorgfältige Bedienung und Instandhaltung voraus.
Eine andere oder darüber hinausgehende Benutzung gilt als nicht
bestimmungsgemäß. Für hieraus resultierende Schäden haftet
Bürkert nicht. Das Risiko trägt allein der Anwender.
• Das Gerät nur bestimmungsgemäß einsetzen.

2.1.

BeschränkungenBei der Ausfuhr des Systems/Gerätes gegebenenfalls bestehende
Beschränkungen beachten.

2.2.

EX Zulassung

Die EX Zulassung ist nur gültig, wenn die von Bürkert zugelassenen
Module und Komponenten so verwendet werden, wie es in dieser
Bedienungsanleitung beschrieben ist.
Der Typ 6013 darf nur in Kombination mit den von Bürkert freigegebenen Zusatzkomponenten eingesetzt werden, andernfalls erlischt die
EX Zulassung!!
Bei unzulässigen Veränderungen am Gerät, Modulen oder Komponenten, erlischt die EX Zulassung ebenfalls.

deutsch19

PTB 00 ATEX 2129 X
Grundlegende Sicherheitshinweise

3.

GRUNDLEGENDESICHERHEITSHINWEISE

Diese Sicherheitshinweise berücksichtigen keine• Zufälligkeiten und Ereignisse, die bei Montage, Betrieb und Wartung
der Geräte auftreten können.
• ortsbezogenen Sicherheitsbestimmungen, für deren Einhaltung, auchin Bezug auf das Montagepersonal, der Betreiber verantwortlich ist.

Explosionsgefahr durch elektrostatische Aufladung!
Bei plötzlicher Entladung elektrostatisch aufgeladener Geräte oder
Personen besteht im EX-Bereich Explosionsgefahr.
• Durch geeignete Maßnahmen sicherstellen, dass es im EX Bereich zu keinen elektrostatischen Aufladungen kommen kann.
• Die Geräteoberfläche nur durch leichtes Abwischen mit einem
feuchten oder antistatischen Tuch reinigen.
Allgemeine Gefahrensituationen.

Explosionsgefahr!
• Das Gerät ist Teil eines geschlossenen Systems und darf nicht
während des Betriebs demontiert werden.
Gefahr durch elektrische Spannung!
Akute Verletzungsgefahr durch gefährliche Körperspannung!
Gefahr der Beschädigung des Gerätes durch Kurzschluss!
• Vor Eingriffen in das Gerät oder die Anlage, Spannung abschalten
und vor Wiedereinschalten sichern!
• Die geltenden Unfallverhütungs- und Sicherheitsbestimmungenfür elektrische Geräte beachten!
Gefahr durch hohen Druck!
Bei Eingriffen in das System besteht akute Verletzungsgefahr.
• Vor dem Lösen von Leitungen und Ventilen den Druck abschalten
und die Leitungen entlüften.
• Beim Einbau die Durchflussrichtung beachten.
• Die geltenden Unfallverhütungs- und Sicherheitsbestimmungenfür druckbeaufschlagte Geräte einhalten.
20

deutschZum Schutz vor Verletzungen ist zu beachten:• Dass die Anlage nicht unbeabsichtigt betätigt werden kann.
• Installations- und Instandhaltungsarbeiten dürfen nur von autorisiertem Fachpersonal mit geeignetem Werkzeug ausgeführt
werden.
• Nach einer Unterbrechung der elektrischen oder pneumatischen
Versorgung ist ein definierter oder kontrollierter Wiederanlauf desProzesses zu gewährleisten.
• Das Gerät darf nur in einwandfreiem Zustand und unter Beachtung
der Bedienungsanleitung betrieben werden.
• Für die Einsatzplanung und den Betrieb des Gerätes müssen die
allgemeinen Regeln der Technik eingehalten werden.
Bei Nichtbeachtung dieser Bedienungsanleitung und ihrer
Hinweise sowie bei unzulässigen Eingriffen in das Gerät entfällt
jegliche Haftung unsererseits, ebenso erlischt die Gewährleistung auf Geräte und Zubehörteile!

PTB 00 ATEX 2129 X
Allgemeine Hinweise

4.

ALLGEMEINE HINWEISE

4.1.

Kontaktadresse

Deutschland
Bürkert Fluid Control Systems
Sales Center
Christian-Bürkert-Str. 13-17
D-74653 IngelfingenTel.  + 49 (0) 7940 - 10 91 111
Fax  + 49 (0) 7940 - 10 91 448
E-mail: info@de.buerkert.com
International
Die Kontaktadressen finden Sie auf den letzten Seiten der gedruckten
Bedienungsanleitung.
Außerdem im Internet unter: www.burkert.com

4.2.

Gewährleistung

Voraussetzung für die Gewährleistung ist der bestimmungsgemäße Gebrauch des Gerätes unter Beachtung der spezifizierten
Einsatzbedingungen.

4.3.

5.

EINSATZBEDINGUNGEN DERGERÄTE

5.1.

Kurzschlussschutz

Jedem Magneten muss als Kurzschlussschutz eine seinem Bemessungsstrom entsprechende Sicherung (max. 3 x Ib nach IEC 601272-1) bzw. ein Motorschutzschalter mit Kurzschluss- und thermischer
Schnellauslösung (Einstellung auf Bemessungsstrom) vorgeschaltet
werden. Bei sehr kleinen Bemessungsströmen des Magneten ist die
Sicherung mit dem kleinsten Stromwert nach der genannten IEC-Normausreichend. Diese Sicherung darf im zugehörigen Versorgungsgerät
untergebracht sein oder muss separat vorgeschaltet werden. Die
Sicherungs-Bemessungsspannung muss gleich oder größer als die
angegebene Nennspannung des Magneten sein. Das Ausschaltvermögen des Sicherungseinsatzes muss gleich oder größer als dermaximal anzunehmende Kurzschlussstrom am Einbauort (üblicherweise1500 A) sein.
Der Sicherungsnennwert ist auf
dem Magneten angegeben.

Informationen im Internet

Sicherung / Fuse
0,08 A

Bedienungsanleitungen und Datenblätter zum Typ 6013 finden Sie im
Internet unter: www.buerkert.dedeutsch21

PTB 00 ATEX 2129 X
Einsatzbedingungen der Geräte

5.2.

Betrieb nur mit zugehörigem
VentilDie Magnetspulen Typ AC10 - PD73 bis AC10 - PD86 dürfen nur
mit zugehörigem Ventilkörper als Komplettgerät betrieben werden, derfolgenden Forderungen entspricht:• Werkstoffe bei Einzel- und Blockmontage:
Metall (Messing, Aluminium, Edelstahl) oder Kunststoff (z. B.
Polyamid PA 6 GV).
GEFAHR!
Explosionsgefahr!
• Bei Einsatz der Geräte in Tanksäulen zur Steuerung von Benzin als
Kategorie 2 muss ein Ventilkörper aus Metall (Messing, Aluminium
oder Edelstahl) verwendet werden.
Mindestbemessungen der Ventilkörper:• 32 mm x 32 mm x 10 mm (L x B x H)
Ein größerer Ventilkörper mit besserer Wärmeleitfähigkeit darf
jeder Zeit angebaut werden.

5.3.

Einzelmontage

Die Magnetspulen Typ AC10 - PD47 bis AC - PD72 sind nur zur
Einzelmontage geeignet.

5.4.

Einsatztemperaturbereich

Für jeden Typ den bei den Elektrischen Daten aufgeführten Einsatztemperaturbereich beachten.
22deutsch5.5.

Umgebungstemperatur > 55 °C

Bei den Magnetspulen Typ AC10 - 6 - PD53 und AC10 - 6 - PD66
für eine Umgebungstemperatur > 55 °C wird ein wärmebeständiger
Kabel eingesetzt.

5.6.

Einsatz in TanksäulenGEFAHR!

Explosionsgefahr durch Öffnen des Gerätes!
• Das Gerät ist ein geschlossenes System. Es darf nicht demontiert
werden!
Explosionsgefahr!
• Bei Einsatz der Geräte in Tanksäulen zur Steuerung von Benzin als
Kategorie 2 muss ein Ventilkörper aus Metall (Messing, Aluminium
oder Edelstahl) verwendet werden.
Die Magnetspule Typ AC10 darf auch zur Steuerung von Benzin in
Kategorie 2 eingesetzt werden, wenn in dem geschlossenen Systemkeine Luft und kein Sauerstoff vorhanden ist.
Dies gilt auch beim Anfahren und Abschalten des Systems.
• Die Spule ist auf dem Kernführungsrohr montiert.
• Die Ventile stellen immer ein geschlossenes System dar.
Die Magnetspulen dürfen nur vom Hersteller demontiert
werden!

PTB 00 ATEX 2129 X
Einsatzbedingungen der Geräte

5.7.

GEFAHR!

Spule AC10

Gerätesteckdose mit
Kabel

Temperaturverhältnisse bei 60 °C.
Umgebungstemperatur an der Magnetspule AC10
Temperaturklasse

Spulengröße

Absoluttemperatur
[°C]

T4

5

118

6

113

4

93

5

87

6

90

5

79

6

75

T5

T6

Ausführung mit einem
Klemmenkasten

Explosionsgefahr!
• Nur festgelegte Kabel und Leitungen dürfen eingeführt werden.
• Betreiber muss eine entsprechende Zugentlastung gewährleisten.
• Es können Leitungen mit Außendurchmesser von 6 mm bis 13 mm
verwendet werden. Beachten Sie die maximale thermische Belastung der eingeführten Kabel bzw. Leitungen.
• Die eingelegte Dichtung muss dem Durchmesser des Kabel /Leitung angepasst werden.
• Der Bemessungsquerschnitt der Kabel / Leitungsadern muss mindestens 0,75 mm² betragen und darf 2,5 mm² nicht überschreiten.
• Schrauben zur Befestigung des Deckels des Klemmenkastensmüssen mit einem Drehmoment von 100 Ncm (± 5 %) angezogen
werden.
• Die Klemmen müssen mit einem Drehmoment von 1–1,5 Nmangezogen werden.
Die Magnetspule AC10 darf auch mit einem Klemmenkasten ausgeführt werden.
Durch den Anbau eines Klemmenkastens ändert sich die Zündschutzart
dieser Magnetspulen.
Kennzeichnung mit angebautem Klemmenkasten:
II 2G/D EX em II T4, T5, T6

deutsch23

PTB 00 ATEX 2129 X
Technische Daten

6.

TECHNISCHE DATEN

6.1.

Konformität

6.4.

WARNUNG!

Das Gerät ist konform zu den EG-Richtlinien entsprechend der
EG-Konformitätserklärung.

6.2.

Betriebsbedingungen

NormenDurch folgende Normen wird die Konformität mit den EG-Richtlinien
erfüllt:

Explosionsgefahr!
Überschreitung der auf dem Typenschild angegebenen technischen
Daten führt zu hohem Risiko!
• Auf dem Typenschild angegebenen technischen Daten keinesfallsüberschreiten.

• EN 60079-0, EN 60079-7, EN 60079-18, EN 61241-0,
EN 61241-1, EN 13463-1

6.3.

ZulassungenCE - Kennzeichnung

Die EG-Baumusterprüfbescheinigung PTB 00 ATEX 2129 X wurde
von der

PTB - Zulassungsnummer

PTB (Physikalisch Technische Bundesanstalt)
Bundesallee 100

Typenschild38116 Braunschweig

Sicherung / Fuse
0,08 Aausgestellt, die auch die Fertigung auditiert (CE 102).
Die EG-Baumusterprüfbescheinigung finden Sie im Internet unter:www.buerkert.de
Bild 1:24

deutschLage des Typenschildes

PTB 00 ATEX 2129 X
Technische Daten

6.4.1.

Typenschild
IEC EX - Zulassungsnummer
Schutzart / Temperaturklasse

D-74653 Ingelfingen

EX - CodeII2 G Ex em II T4/T5/T6
II2 D IP65 T=135°C
IEC Ex PTB 07.0021X
AC10-Z3-5 24V ~ 7W
S/N XXXXXXXXXXXX

W22LS

Identnummer der Spule
Seriennummer der Spule
Spulentyp, Spannung, Leistung

Bild 2:Beschreibung des Typenschildes

6.5.

Elektrische Daten

6.5.1.

Spulen für Einzelmontage

Universalstrom, Nennspannung 12 ... 400 V, Frequenz 0 ... 60 Hz
SpulentypBemessungsstrom [A]Grenzleistung[W]

Max. zul.
Umgebungstemperatur [°C]

Temperaturklasse

AC10-5-PD47

0,68 ... 0,02

7-30 ... +60

T4

AC10-5-PD48

0,33 ... 0,01

4-30 ... +50

T5

AC10-5-PD49

0,25 ... 0,007

3-30 ... +60

T5

AC10-5-PD50

0,25 ... 0,007

3-30 ... +40

T6

AC10-5-PD51

0,19 ... 0,005

2,25-30 ... +50

T6

AC10-5-PD52

0,114 ... 0,003

1,25-30 ... +60

T6

AC10-6-PD53

0,8 ... 0,02

9-30 ... +60

T4

AC10-6-PD54

0,31 ... 0,009

3,5-30 ... +60

T5

AC10-6-PD55

0,16 ... 0,005

1,8-30 ... +60

T6

AC10-4-PD56

0,35 ... 0,01

4-30 ... +50

T5

AC10-4-PD57

0,25 ... 0,007

3-30 ... +60

T5

AC10-4-PD59

0,13 ... 0,003

1,5-30 ... +60

T6

AC10-5-PD60

0,68 ... 0,02

7

-40 ... +60

T4

AC10-5-PD61

0,33 ... 0,01

4-40 ... +50

T5

AC10-5-PD62

0,25 ... 0,007

3-40 ... +60

T5

AC10-5-PD63

0,25 ... 0,007

3-40 ... +40

T6deutsch25

PTB 00 ATEX 2129 X
Technische Daten

AC10-5-PD64

0,19 ... 0,005

2,25-40 ... +50

T6

AC10-5-PD65

0,114 ... 0,003

1,25-40 ... +60

T6

AC10-6-PD66

0,8 ... 0,02

9-40 ... +60

T4

AC10-6-PD67

0,31 ... 0,009

3,5-40 ... +60

T5

AC10-6-PD68

0,16 ... 0,005

1,8-40 ... +60

T6

AC10-4-PD69

0,35 ... 0,01

4-40 ... +50

T5

AC10-4-PD70

0,25 ... 0,007

3-40 ... +60

T5

AC10-4-PD72

0,13 ... 0,003

1,5-40 ... +60

T6

6.5.2.

Universalstrom, Nennspannung 12 ... 400 V, Frequenz 0 ... 60 Hz

Spulen für Einzel- oder
Batteriemontage

GEFAHR!

SpulentypBemessungsstrom [A]Grenzleistung
[W]

Max.
zul. Umgebungstemperatur [°C]

Temperaturklasse

1)AC10-5-PD73

0,68 ... 0,02

7-30 ... +40

T4

1

AC10-5-PD74

0,25 ... 0,007

3-30 ... +50

T5

1

AC10-5-PD75

0,19 ... 0,005

2,25-30 ... +40

T6

1

AC10-5-PD76

0,114 ... 0,003

1,25-30 ... +60

T6

1

AC10-4-PD77

0,33 ... 0,01

4-30 ... +40

T5

5

AC10-4-PD78

0,25 ... 0,007

3-30 ... +50

T6

5

AC10-4-PD79

0,13 ... 0,003

1,5-30 ... +55

T6

5

AC10-5-PD80

0,68 ... 0,02

7

-40 ... +40

T4

1

Explosionsgefahr durch Überhitzung!

AC10-5-PD81

0,25 ... 0,007

3-40 ... +50

T51

Bei Batteriemontage sind folgende Daten der Ventile einzuhalten:• Abmessung des Ventilkörpers: 32 mm x 32 mm x 10 mm.
• Material des Ventilkörpers: Messing (MS), Aluminium (AL),
Edelstahl (VA) oder Kunststoff (PA 6 GV).

AC10-5-PD82

0,19 ... 0,005

2,25-40 ... +40

T6

1

AC10-5-PD83

0,114 ... 0,003

1,25-40 ... +60

T6

1

AC10-4-PD84

0,33 ... 0,01

4-40 ... +40

T5

5

AC10-4-PD85

0,25 ... 0,007

3-40 ... +50

T5

5

AC10-4-PD86

0,13 ... 0,003

1,5-40 ... +55

T6

5

1)

26

deutschBei Batteriemontage: min. Abstand zur Wand [mm]PTB 00 ATEX 2129 X
Montage

7.

MONTAGE

7.1.

Sicherheitshinweise

GEFAHR!
Gefahr durch elektrische Spannung!

Folgende Sicherheitshinweise sind einzuhalten:• Die Oberfläche des Gerätes kann sich elektrostatisch aufladen. In
explosionsgefährdeten Bereichen darf die Oberfläche der Geräte
nur mit einem feuchten oder antistatischen Tuch gereinigt werden.
• Nur festgelegte Kabel und Leitungen dürfen eingeführt werden.

Akute Verletzungsgefahr durch gefährliche Körperspannung!
Gefahr der Beschädigung des Gerätes durch Kurzschluss!
• Vor Eingriffen in das Gerät oder die Anlage, Spannung abschalten
und vor Wiedereinschalten sichern!
• Spannungsführende Klemmen im Klemmenkasten können Stromschlag, Kurzschluss oder Explosion verursachen. Spannung
abschalten. Erst dann den Klemmenkasten öffnen.
• Die Anschlussleitungen der Elektromagneten müssen fest undso verlegt werden, dass sie vor mechanischen Beschädigungenhinreichend geschützt sind.
• Die geltenden Unfallverhütungs- und Sicherheitsbestimmungenfür elektrische Geräte beachten!

• Betreiber muss eine entsprechende Zugentlastung gewährleisten.

Explosionsgefahr durch Überhitzung!

• Leitungen mit Außendurchmesser von 6 mm ... 13 mm können
verwendet werden. Die maximale thermische Belastung der eingeführten Kabel bzw. Leitungen beachten.

Bei Batteriemontage sind folgende Daten der Ventile einzuhalten:• Abmessung des Ventilkörpers: 32 mm x 32 mm x 10 mm.
• Material des Ventilkörpers: Messing (MS), Aluminium (AL),
Edelstahl (VA) oder Kunststoff (PA 6 GV).

GEFAHR!
Explosionsgefahr!
Das Gerät ist ein geschlossenes System. Es darf nicht demontiert
werden.

• Die eingelegte Dichtung muss dem Durchmesser des Kabels /der Leitung angepasst werden.
Der Bemessungsquerschnitt der Kabel / Leitungsadernmuss mindestens 0,75 mm² betragen und darf 2,5 mm² nichtüberschreiten.
• Die Schrauben zur Befestigung des Deckels des Klemmenkastensmüssen mit einem Drehmoment von 100 Ncm (± 5 %) angezogen
werden.

WARNUNG!
Gefahr durch hohen Druck!
• Vor dem Lösen von Leitungen und Ventilen den Druck abschalten und die Leitungen entlüften.
• Beim Einbau die Durchflussrichtung beachten.
• Die geltenden Unfallverhütungs- und Sicherheitsbestimmungenfür druckbeaufschlagte Geräte einhalten.

deutsch27

PTB 00 ATEX 2129 X
Inbetriebnahme

7.2.

Montage des Typs 6013
Einbaulage beliebig.
Vorzugsweise mit Magnetsystem oben.

8.

INBETRIEBNAHME

8.1.

Sicherheitshinweise
WARNUNG!

1. Rohrleitungen reinigen.
2. Einbaulage beliebig

Verletzungsgefahr bei unsachgemäßem Betrieb!

→→Vorzugsrichtung mit Antrieb oben.

Nicht sachgemäßer Betrieb kann zu Verletzungen, sowie Schäden
am Gerät und seiner Umgebung führen.
• Vor der Inbetriebnahme muss gewährleistet sein, dass der Inhalt
der Bedienungsanleitung dem Bedienungspersonal bekannt ist
und vollständig verstanden wurde.
• Die Sicherheitshinweise und die bestimmungsgemäße Verwendung müssen beachtet werden.
• Nur ausreichend geschultes Personal darf die Anlage/das Gerät
in Betrieb nehmen.

3. Schmutzfänger vorschalten→→Durchflussrichtung beachten!
4. Abdichten→→PTFE.

5. Rohrleitungen einschrauben→→Durchflussrichtung beachten!
6. Montieren / Demontieren.
HINWEIS!

8.2.

Hinweis für Geräte mit Anschlusskabel:

Vor Inbetriebnahme sicherstellen, dass:

Anschlusskabel und Spule sind vergossen. Sie dürfen nicht
demontiert werden!

• das Gerät vorschriftsmäßig installiert wurde,• der Anschluss ordnungsgemäß ausgeführt wurde,• das Gerät nicht beschädigt ist,

Schutzleiter immer anschließen!

• alle Schrauben fest angezogen sind.

7. Elektrisch anschließen.

28

Inbetriebnahme

deutschPTB 00 ATEX 2129 X
Wartung, Fehlerbehebung

9.
9.1.

WARTUNG,
FEHLERBEHEBUNG
Sicherheitshinweise
WARNUNG!

9.2.

Wartungsarbeiten

Die Geräte sind beim Betrieb unter den in dieser Anleitung beschriebenen Bedingungen wartungsfrei.

9.3.

Fehlerbehebung

Bei Störungen sicherstellen, dass:

Explosionsgefahr durch elektrostatische Aufladung!

• das Gerät vorschriftsmäßig installiert wurde,

Bei plötzlicher Entladung elektrostatisch aufgeladener Geräte oder
Personen besteht im EX-Bereich Explosionsgefahr.
• Durch geeignete Maßnahmen sicherstellen, dass es im EXBereich zu keinen elektrostatischen Aufladungen kommen kann.
• Die Geräteoberfläche nur durch leichtes Abwischen mit einem
feuchten oder antistatischen Tuch reinigen.

• der Anschluss ordnungsgemäß ausgeführt wurde,• das Gerät nicht beschädigt ist,
• alle Schrauben fest angezogen sind,• Spannung und Druck anliegen,• die Rohrleitungen frei sind.

Verletzungsgefahr bei unsachgemäßen Wartungs-, Reparatur
und Instandhaltungsarbeiten!
• Die Wartungs- und Instandhaltungsarbeiten am Gerät dürfen nur
autorisiertes Fachpersonal mit geeignetem Werkzeug durchführen!
• Reparaturen am Gerät dürfen nur vom Hersteller durchgeführt
werden!
• Bei Repatatur- oder Wartungsarbeiten an der Anlage darf das
Ventil nicht geöffnet und die Schutzleiterverbindung nicht getrennt
werden!

deutsch29

PTB 00 ATEX 2129 X
Zubehör

10.

ZUBEHÖR

11.

10.1.

Sicherheitshinweise

TRANSPORT, LAGERUNG,
VERPACKUNGHINWEIS!

VORSICHT!

Transportschäden!

Verletzungsgefahr, Sachschäden durch falsche Teile!
Falsches Zubehör und ungeeignete Ersatzteile können Verletzungen
und Schäden am Gerät und dessen Umgebung verursachen.
• Nur Originalzubehör sowie Originalersatzteile der Fa. Bürkert
verwenden.
Bei Ausführung der Geräte mit Klemmenkasten kann in Temperaturklasse T4, die Sicherung des Typs 1058 mit Zulassung PTB 01 ATEX
2064 U eingesetzt werden.

Unzureichend geschützte Geräte können durch den Transport
beschädigt werden.
• Gerät vor Nässe und Schmutz geschützt in einer stoßfesten
Verpackung transportieren.
• Eine Über- bzw. Unterschreitung der zulässigen Lagertemperatur vermeiden.
Falsche Lagerung kann Schäden am Gerät verursachen.
• Gerät trocken und staubfrei lagern!

SicherungTyp 1058

Bestell.-Nr.

SicherungTyp 1058

Bestell.-Nr.

• Lagertemperatur. -40 … +55 °C.     0,063 A

153 7170,500 A

153 735

Umweltschäden durch von Medien kontaminierte Geräteteile.

0,080 A

153 745

0,630 A

153 736• Gerät und Verpackung umweltgerecht entsorgen!

0,100 A

153 7180,800 A

153 737

0,125 A

153 719

1,000 A

153 738• Geltende Entsorgungsvorschriften und Umweltbestimmungeneinhalten.

0,160 A

153 720

1,250 A

153 7390,200 A

153 7311,600 A

153 746

0,315 A

153 733

2,000 A

153 740

0,400 A

153 734

3,150 A

153 74230

deutschPTB 00 ATEX 2129 X
Sommaire﻿
1. LES INSTRUCTIONS DE SERVICE...................................................... 32
1.1. Symboles..........................................................................................32
2. UTILISATION CONFORME....................................................................... 33
2.1. Limitations.........................................................................................33
2.2. Homologation EX............................................................................33
3. CONSIGNES DE SÉCURITÉ FONDAMENTALES.......................... 34
4. INDICATIONS GÉNÉRALES..................................................................... 35
4.1. Adresses...........................................................................................35
4.2. Garantie légale.................................................................................35
4.3. Informations sur Internet................................................................35
5. CONDITIONS D’UTILISATION DE L’APPAREIL.............................. 35
5.1. Protection contre les courts-circuits..........................................35
5.2. Exploitation avec vanne correspondante...................................36
5.3. Montage individuel..........................................................................36
5.4. Plage de température d’utilisation...............................................36
5.5. Température ambiante > 55 °C...................................................36
5.6. Utilisation dans les pompes à essence......................................36
5.7. Modèle avec coffret à bornes.......................................................37

7. MONTAGE......................................................................................................... 41
7.1. Consignes de sécurité...................................................................41
7.2. Montage du type 6013..................................................................42
8. MISE EN SERVICE........................................................................................ 42
8.1. Consignes de sécurité...................................................................428.2. Mise en service................................................................................42
9. MAINTENANCE, DÉPANNAGE............................................................... 43
9.1. Consignes de sécurité...................................................................43
9.2. Travaux d’entretien..........................................................................43
9.3. Dépannage.......................................................................................43
10. ACCESSOIRES............................................................................................ 44
10.1. Consignes de sécurité.................................................................44
11. TRANSPORT, STOCKAGE, ÉLIMINATION...................................... 44

6. CARACTÉRISTIQUES TECHNIQUES................................................. 38
6.1. Conformité........................................................................................38
6.2. Normes..............................................................................................38
6.3. Homologations.................................................................................38
6.4. Conditions d’exploitation...............................................................38
6.5. Caractéristiques électriques.........................................................39

français

31

PTB 00 ATEX 2129 X
Les instructions de service

1.

LES INSTRUCTIONS DESERVICELes instructions de service décrivent le cycle de vie complet de l’appareil. Conservez ces instructions de sorte qu’elles soient accessibles
à tout utilisateur et à disposition de tout nouveau propriétaire.
Les instructions de service contiennent des informations
importantes sur la sécurité !
Le non-respect de ces consignes peut entraîner des situations
dangereuses.
• Les instructions de service doivent être lues et comprises.

ATTENTION !
Met en garde contre un risque possible !
• Le non-respect peut entraîner des blessures légères ou demoyenne gravité.
REMARQUE !
Met en garde contre des dommages matériels !
• L’appareil ou l’installation peut être endommagé(e) en cas denon-respect.

Désigne des informations supplémentaires importantes, desconseils et des recommandations d’importance.

1.1.

SymbolesDANGER !

Met en garde contre un danger imminent !
• Le non-respect peut entraîner la mort ou de graves blessures.

Renvoie à des informations dans ces instructions de service
ou dans d’autres documentations.

→→identifie une opération que vous devez effectuer.

AVERTISSEMENT !
Met en garde contre une situation éventuellement dangereuse !
• Risque de blessures graves, voire la mort en cas de non-respect.

32

français

PTB 00 ATEX 2129 X
Utilisation conforme

2.

UTILISATION CONFORME

L’utilisation non conforme de l’appareil du type 6013 peut présenter des dangers pour les personnes, les installations proches
et l’environnement.
• L’appareil sert exclusivement d’électrovanne pour les fluides autorisés par la fiche technique et pour l’utilisation dans les groupes
d’explosion II, catégorie 2G ou 2D et classe de température T4,T5 ou T6 (voir les données sur laplaque d’homologation).
• L’appareil peut être employé uniquement pour les cas individuels
prévus dans le chapitre « 5. Conditions d’utilisation de l’appareil »et en association avec les appareils et composants étrangers
recommandés et homologués par Bürkert.
• Le type de protection employé est l’encapsulage EX « m » pourbobines avec raccordement câble ou l’encapsulage avec sécurité
augmentée EX « em » pour bobines avec coffret à bornes.
• Respecter les exigences de la norme EN 61241-0/-1 par ex. ence qui concerne les dépôts de poussière et les températures.
• La bobine magnétique AC10 sert à actionner les vannes qui
commandent des fluides liquides ou gazeux. L’appareil fait partie
d’un système fermé et peut être utilisé également dans les pompes
à essence pour commander l’essence en tant qu’appareil decatégorie 2.
• L’exploitation impeccable et sûre du système suppose un transport
conforme, un stockage et une installation conformes ainsi qu’uneutilisation et une maintenance soigneuses. Toute autre utilisation
est considérée comme non conforme. Bürkert n’est pas responsable des dommages en résultant. L’utilisateur est seul à ensupporter le risque.
• L’appareil doit être utilisé seulement de façon conforme.

français

2.1.

Limitations

Lors de l’exportation du système / de l’appareil, veuillez respecter leslimitations éventuelles existantes.

2.2.

Homologation EX

L’homologation EX n’est valable que si vous utilisez les modules etcomposants homologués par Bürkert tel que cela est décrit dans ces
instructions de service.
Le type 6013 ne doit être utilisé qu’avec les composants supplémentaires autorisés par Bürkert, sinon l’homologation EX devient caduque.
En cas de modification non autorisée de l’appareil, des modules ou descomposants, l’homologation EX devient également caduque.

33

PTB 00 ATEX 2129 X
Consignes de sécurité fondamentales

3.

CONSIGNES DE SÉCURITÉFONDAMENTALES

Ces consignes de sécurité ne tiennent pas compte• Des hasards et des événements pouvant survenir lors du montage,de l’exploitation et de l’entretien des appareils.
• Des prescriptions de sécurité locales que l’exploitant est tenu defaire respecter par le personnel chargé du montage.

Risque d’explosion !
• L’appareil fait partie d’un système clos et ne peut pas être démonté
pendant l’exploitation.
Danger présenté par la tension électrique !
Danger important de blessures par tensions dangereuses au niveau
du corps ! Danger d’endommagement de l’appareil par court-circuit !
• Avant d’intervenir dans l’appareil ou l’installation, couper la tension
et empêcher toute remise sous tension par inadvertance !
• Veuillez respecter les réglementations en vigueur pour les appareilsélectriques en matière de prévention des accidents ainsi qu’enmatière de sécurité !
Danger dû à la haute pression !
Il y a risque important de blessures lors d’interventions sur le système.
• Avant de desserrer les conduites et les vannes, coupez la pression
et assurez l’échappement de l’air des conduites.
• Lors du montage, respectez le sens du débit.
• Veuillez respecter les réglementations en vigueur pour les appareils
sous pression en matière de prévention des accidents ainsi qu’enmatière de sécurité.
34

Risque d’explosion dû à la charge électrostatique !
Il y a risque d’explosion en cas de décharge soudaine d’appareils
ou de personnes chargés d’électricité statique dans des zones
présentant des risques d’explosion.
• Assurez-vous par des mesures appropriées, qu’il ne peut y avoir
de charges électrostatiques dans de telles zones présentant
des risques d’explosion.
• Ne nettoyer la surface de l’appareil que par un essuyage léger
avec un chiffon humide ou antistatique.
Situations dangereuses d’ordre général.
Pour prévenir les blessures, respecter ce qui suit :• L’installation ne peut pas être actionnée par inadvertance.
• Les travaux d’installation et de maintenance doivent être effectués
uniquement par des techniciens qualifiés et habilités disposant del’outillage approprié.
• Après une interruption de l’alimentation électrique ou pneumatique,un redémarrage défini ou contrôlé du processus doit être garanti.
• L’appareil doit être utilisé uniquement en parfait état et en respectant les instructions de service.
• Les règles générales de la technique sont d’application pour planifier
l’utilisation et utiliser l’appareil.
Le non-respect de ces instructions de service avec ses
consignes ainsi que les interventions non autorisées sur l’appareil
excluent toute responsabilité de notre part et entraînent la nullitéde la garantie légale concernant les appareils et les accessoires !

français

PTB 00 ATEX 2129 X
Indications générales

4.

INDICATIONS GÉNÉRALES

4.1.

Adresses

Allemagne
Bürkert Fluid Control Systems
Sales Center
Christian-Bürkert-Str. 13-17
D-74653 IngelfingenTel.  + 49 (0) 7940 - 10 91 111
Fax  + 49 (0) 7940 - 10 91 448
E-mail: info@de.buerkert.com
International
Les adresses se trouvent aux dernières pages des instructions deservice imprimées.
Egalement sur internet sous : www.burkert.com

4.2.

Garantie légale

La condition pour bénéficier de la garantie légale est l’utilisation
conforme de l’appareil dans le respect des conditions d’utilisation
spécifiées.

4.3.

Informations sur Internet

Vous trouverez les instructions de service et les fiches techniques
concernant le type 6013 sur Internet sous : www.buerkert.fr

français

5.

CONDITIONS D’UTILISATION
DE L’APPAREIL

5.1.

Protection contre lescourts-circuits

Pour assurer la protection contre les courts-circuits, il convient deplacer en amont de chaque aimant un fusible correspondant à soncourant évalué (maxi 3 x Ib selon CEI 60127-2-1) ou un disjoncteur-protecteur à déclenchement rapide thermique et de court-circuit (réglage
sur le courant évalué). Selon la norme CEI citée, le fusible à la valeurde courant le plus faible suffit lorsque les courants mesurés de l’aimantsont très faibles. Ce fusible peut être logé dans l’appareil d’alimentation
correspondant ou placé séparément en amont. La tension mesurée du
fusible doit être identique ou supérieure à la tension nominale indiquéede l’aimant. La puissance de coupure du fusible doit être identique ou
supérieure au courant de court-circuit maximal possible sur le lieu demontage (habituellement 1500 A).
La valeur nominale du fusible est
indiquée sur la bobine.

Sécurité / Fusible
0,08 A

35

PTB 00 ATEX 2129 X
Conditions d’utilisation de l’appareil

5.2.

Exploitation avec vannecorrespondante

Les bobines magnétiques des types AC10 - PD73 à AC10 - PD86
doivent être utilisées uniquement avec le corps de vanne qui s’yrapporte en tant qu’appareil complet correspondant aux exigencessuivantes :• Matériaux en montage unique ou en bloc :Métal (laiton, aluminium, inox) ou plastique (par ex. Polyamide PA
6 GV).
DANGER !
Risque d’explosion !
• Lors de l’utilisation des appareils dans des pompes à essence
pour la commande d’essence de catégorie 2, un corps de vanneen métal (laiton, aluminium, inox) doit être employé.
Dimensionnements du corps de vanne :• 32 mm x 32 mm x 10 mm (L x l x h)
Il est possible d’utiliser à tout moment un corps de soupape plus
grand avec une meilleure conductibilité thermique.

5.3.

Montage individuel

Seules les bobines magnétiques de type AC10 - PD47 et AC - PD72
sont adaptées au montage individuel.

5.4.

Plage de température d’utilisation

Respecter la plage de température d’utilisation indiquée dans lesdonnées électriques pour chaque type.
36

5.5.

Température ambiante > 55 °C

En présence d’une température > 55 °C, un câble résistant à la chaleur
est utilisé pour les bobines magnétiques des types AC10 - 6 - PD53
et AC10 - 6 - PD66 .

5.6.

Utilisation dans les pompes àessence
DANGER !

Danger d’explosion en ouvrant l’appareil !
• L’appareil est un système clos. Il ne doit pas être démonté !
Risque d’explosion !
• Lors de l’utilisation des appareils dans des pompes à essence
pour la commande d’essence de catégorie 2, un corps de vanneen métal (laiton, aluminium, inox) doit être employé.
Les appareils doivent être également utilisés pour la commanded’essence de catégorie 2 quand aucun air ou oxygène n’est présent
dans le système clos.
Cela est également valable lors du démarrage ou de l’arrêt dusystème.
• La bobine est montée sur le tube de guidage du noyau.
• Les vannes représentent toujours un système clos.
Les bobines magnétiques ne doivent être démontées quepar le constructeur !

français

PTB 00 ATEX 2129 X
Conditions d’utilisation de l’appareil

5.7.

Modèle avec coffret à bornes
DANGER !

Bobine AC10

Prise d’appareil avec
câble

Conditions de température à 60 °C.
Température ambiante sur la bobine magnétique AC10.
Classe detempérature

Taille de bobine

Température
absolue [°C]

T4

5

118

6

113

4

93

5

87

6

90

5

79

6

75

T5

T6

français

Risque d’explosion !
• Seuls des câbles et des conduites fixés doivent être installés.
• L’exploitant doit garantir une décharge de traction correspondante.
• Des conduites avec diamètre extérieur de 6 mm à 13 mm peuventêtre utilisées. Respecter la contrainte thermique maximale du câbleou de la conduite utilisée.
• Le joint inséré doit être adapté au diamètre du câble / de laconduite utilisés.
• La section de base pour le calcul de l’âme du câble / de la conduite
doit être de 0,75 mm² minimum et ne doit pas dépasser 2,5 mm².
• Les vis pour la fixation du couvercle du coffret à bornes doiventêtre serrées avec un couple de serrage de 100 Ncm (± 5 %).
• Les bornes doivent être serrées avec un couple de serrage de
1–1,5 Nm.
Les bobines magnétiques AC10 peuvent être effectuées avec uncoffret à bornes
Du fait du montage d’un coffret à bornes, le type de protection àl’allumage de ces bobines magnétiques est modifié.
Désignation avec coffret à bornes monté :II 2G/D EX em II T4, T5, T6

37

PTB 00 ATEX 2129 X
Caractéristiques techniques

6.
6.1.

CARACTÉRISTIQUESTECHNIQUES

6.4.

Conformité

Risque d’explosion !

L’appareil est conforme aux directives CE conformément à la déclarationde conformité CE.

6.2.

NormesConditions d’exploitation
AVERTISSEMENT !

Un dépassement des données techniques données sur la plaquesignalétique entraîne un risque élevé !
• Ne dépasser en aucun cas les données techniques données surla plaque signalétique.

La conformité avec les directives CE est satisfaite par les normes
suivantes :• EN 60079-0, EN 60079-7, EN 60079-18, EN 61241-0,
EN 61241-1, EN 13463-1

6.3.

Homologations

Label CEN° d’homologation PTB

Le certificat d’essai de modèle type PTB 00 ATEX 2129 X a étéétabli par le
PTB (Physikalisch Technische Bundesanstalt)
Bundesallee 100
38116 Braunschweig

Plaque signalétique

Sécurité / Fusible
0,08 Aqui effectue également l’audit de production (CE 102).
Le certificat d’essai de modèle CE se trouve sur Internet sous :www.buerkert.fr

38

Fig. 1 :Position de la plaque signalétiquefrançais

PTB 00 ATEX 2129 X
Caractéristiques techniques

6.4.1.

Plaque signalétique
N° d’homologation IEC EX
Type de protection / classe detempérature

D-74653 Ingelfingen

II2 G Ex em II T4/T5/T6
II2 D IP65 T=135°C
IEC Ex PTB 07.0021X
AC10-Z3-5 24V ~ 7W
S/N XXXXX
W22LS

Numéro d’identification de la bobine
Numéro de série de la bobine
Type de bobine, Tension, PuissanceFig. 2 :Caractéristiques électriques

6.5.1.

Bobines pour montage individuel

Courant universel, tension nominale 12 ... 400 V, fréquence 0 ... 60 Hz

EX - CodeXXXXXXX

6.5.

Description de la plaque signalétiquefrançais

Type debobineCourantévalué
[A]

Puissance
limite[W]

Températureambiante maxi[°C]

Classedetempérature

AC10-5-PD47

0,68 ... 0,02

7-30 ... +60

T4

AC10-5-PD48

0,33 ... 0,01

4-30 ... +50

T5

AC10-5-PD49

0,25 ... 0,007

3-30 ... +60

T5

AC10-5-PD50

0,25 ... 0,007

3-30 ... +40

T6

AC10-5-PD51

0,19 ... 0,005

2,25-30 ... +50

T6

AC10-5-PD52

0,114 ... 0,003

1,25-30 ... +60

T6

AC10-6-PD53

0,8 ... 0,02

9-30 ... +60

T4

AC10-6-PD54

0,31 ... 0,009

3,5-30 ... +60

T5

AC10-6-PD55

0,16 ... 0,005

1,8-30 ... +60

T6

AC10-4-PD56

0,35 ... 0,01

4-30 ... +50

T5

AC10-4-PD57

0,25 ... 0,007

3-30 ... +60

T5

AC10-4-PD59

0,13 ... 0,003

1,5-30 ... +60

T6

AC10-5-PD60

0,68 ... 0,02

7

-40 ... +60

T4

AC10-5-PD61

0,33 ... 0,01

4-40 ... +50

T5

AC10-5-PD62

0,25 ... 0,007

3-40 ... +60

T5

39

PTB 00 ATEX 2129 X
Caractéristiques techniques

AC10-5-PD63

0,25 ... 0,007

3-40 ... +40

T6

AC10-5-PD64

0,19 ... 0,005

2,25-40 ... +50

T6

AC10-5-PD65

0,114 ... 0,003

1,25-40 ... +60

T6

AC10-6-PD66

0,8 ... 0,02

9-40 ... +60

T4

AC10-6-PD67

0,31 ... 0,009

3,5-40 ... +60

T5

AC10-6-PD68

0,16 ... 0,005

1,8-40 ... +60

T6

AC10-4-PD69

0,35 ... 0,01

4-40 ... +50

T5

AC10-4-PD70

0,25 ... 0,007

3-40 ... +60

T5

AC10-4-PD72

0,13 ... 0,003

1,5-40 ... +60

T6

Courant universel, tension nominale 12 ... 400 V, fréquence 0 ... 60 Hz
Type debobineCourantévalué
[A]

Puissance
limite[W]

Températureambiante
maxi[°C]Classedetempérature1)

AC10-5-PD73

0,68 ... 0,02

7-30 ... +40

T4

1

AC10-5-PD74

0,25 ... 0,007

3-30 ... +50

T5

1

AC10-5-PD75

0,19 ... 0,005

2,25-30 ... +40

T6

1

AC10-5-PD76

0,114 ... 0,003

1,25-30 ... +60

T6

1

AC10-4-PD77

0,33 ... 0,01

4-30 ... +40

T5

5

AC10-4-PD78

0,25 ... 0,007

3-30 ... +50

T6

5

AC10-4-PD79

0,13 ... 0,003

1,5-30 ... +55

T6

5

AC10-5-PD80

0,68 ... 0,02

7

-40 ... +40

T4

1

AC10-5-PD81

0,25 ... 0,007

3-40 ... +50

T5

1

Risque d’explosion par surchauffe !

AC10-5-PD82

0,19 ... 0,005

2,25-40 ... +40

T61

En cas de montage en batterie, il convient de respecter les caractéristiques suivantes des vannes :• Dimension du corps de vanne : 32 mm x 32 mm x 10 mm.
• Matériau du corps de vanne : laiton (MS), aluminium (AL), acierinoxydable (VA) ou matériau synthétique (PA 6 GV).

AC10-5-PD83

0,114 ... 0,003

1,25-40 ... +60

T6

1

AC10-4-PD84

0,33 ... 0,01

4-40 ... +40

T5

5

AC10-4-PD85

0,25 ... 0,007

3-40 ... +50

T5

5

AC10-4-PD86

0,13 ... 0,003

1,5-40 ... +55

T65

6.5.2.

Bobines pour montage individuel ou
en batterie

DANGER !

1)40

En cas de montage en batterie : distance mini par rapport au mur [mm]français

PTB 00 ATEX 2129 X
Montage

7.

MONTAGE

7.1.

Consignes de sécurité

DANGER !

DANGER !
Risque d’explosion !
L’appareil est un système clos. Il ne doit pas être démonté.
Les indications de sécurité suivantes doivent être respectées :• La surface de l’appareil peut se charger d’électricité statique.
Dans les zones présentant des risques d’explosion, la surface
de l’appareil ne doit être nettoyée qu’avec un chiffon humide ou
antistatique.
• Seuls des câbles et des conduites fixés doivent être installés.
• L’exploitant doit garantir une décharge de traction correspondante.
• Seules les conduites avec un diamètre extérieur de 6 mm ... 13 mm
peuvent être utilisées. Respecter la contrainte thermique maximaledu câble ou de la conduite utilisée.
• Le joint inséré doit être adapté au diamètre du câble / de laconduite.
La section de base pour le calcul de l’âme du câble / de laconduite doit être de 0,75 mm² minimum et ne doit pas dépasser 2,5 mm².
• Les vis pour la fixation du couvercle du coffret à bornes doiventêtre serrées avec un couple de serrage de 100 Ncm (± 5 %).

français

Danger présenté par la tension électrique !
Danger important de blessures par tensions dangereuses au niveau
du corps ! Danger d’endommagement de l’appareil par court-circuit !
• Avant d’intervenir dans l’appareil ou l’installation, couper la tension
et empêcher toute remise sous tension par inadvertance !
• Les bornes conductrices de tension du coffret à bornes peuvent
entraîner des chocs électriques, des court-circuits ou des explosions. Couper la tension. Seulement alors, ouvrir le coffret à bornes.
• Les câbles de raccordement des électro-aimants doivent êtredisposés fixés et de telle façon qu’ils soient suffisamment protégésdes dommages mécaniques.
Risque d’explosion par surchauffe !
En cas de montage en batterie, il convient de respecter les caractéristiques suivantes des vannes :• Dimension du corps de vanne : 32 mm x 32 mm x 10 mm.
• Matériau du corps de vanne : laiton (MS), aluminium (AL), acierinoxydable (VA) ou matériau synthétique (PA 6 GV).
AVERTISSEMENT !
Danger dû à la haute pression !
Il y a risque important de blessures lors d’interventions sur le système.
• Avant de desserrer les conduites et les vannes, coupez la pression et assurez l’échappement de l’air des conduites.
• Lors du montage, respectez le sens du débit.
• Veuillez respecter les réglementations en vigueur pour les appareils sous pression en matière de prévention des accidents ainsiqu’en matière de sécurité.
41

PTB 00 ATEX 2129 X
Mise en service

7.2.

Montage du type 6013
Emplacement de montage libre.
De préférence avec le système magnétique en haut.

1. Nettoyer les tuyauteries.
2. Emplacement de montage libre→→Orientation préférentielle avec l’entraînement en haut.
3. Intercaler un collecteur d’impuretés→→Respectez le sens du débit !
4. Etanchéification→→PTFE.

5. Vissez les tuyauteries→→Respectez le sens du débit !
6. Monter / démonter.
REMARQUE !
Indication pour les appareils avec câble de raccordement :Le câble de raccordement et la bobine sont moulés. Ils ne doiventpas être démontés !
Raccordez toujours le conducteur de protection !

8.

MISE EN SERVICE

8.1.

Consignes de sécurité
AVERTISSEMENT !

Risque de blessures dû à une exploitation non conforme !
Une utilisation non conforme peut entraîner des blessures etendommager l’appareil et son environnement.
• Avant la mise en service, il faut s’assurer que le contenu desinstructions de service est connu et parfaitement compris parles opérateurs.
• Respectez les consignes de sécurité et l’utilisation conforme.
• L’appareil / l’installation doit être mis(e) en service uniquement
par un personnel suffisamment formé.

8.2.

Mise en service

Avant la mise en service, s’assurer que :• l’appareil a été installé dans les règles,• le raccordement a été correctement effectué,• l’appareil n’est pas endommagé,• toutes les vis sont bien serrées.

7. Raccordez à l’électricité.

42

français

PTB 00 ATEX 2129 X
Maintenance, dépannage

9.

MAINTENANCE, DÉPANNAGE

9.2.

9.1.

Consignes de sécurité

Les appareils sont sans entretien lors d’une exploitation sous lesconditions reprises dans ces instructions.

AVERTISSEMENT !

9.3.

Travaux d’entretien

Dépannage

Risque d’explosion dû à la charge électrostatique !

Lors d’incidents, s’assurer que :Il y a risque d’explosion en cas de décharge soudaine d’appareils
ou de personnes chargés d’électricité statique dans des zones
présentant des risques d’explosion.
• Assurez-vous par des mesures appropriées, qu’il ne peut y avoir
de charges électrostatiques dans de telles zones présentant
des risques d’explosion.
• Ne nettoyer la surface de l’appareil que par un essuyage léger
avec un chiffon humide ou antistatique.

• l’appareil a été installé dans les règles,• le raccordement a été correctement effectué,• l’appareil n’est pas endommagé,• toutes les vis sont bien serrées,• la tension et la pression sont disponibles,• les tuyauteries ne sont pas obstruées.

Risque de blessures lors de travaux de maintenance, réparation
et d’entretien non conformes !
• Les travaux de maintenance et d’entretien sur l’appareil ne doiventêtre effectués que par un personnel autorisé et qualifié avec desoutils adaptés !
• Les réparations sur l’appareil doivent être effectuées uniquement
par le fabricant !
• Lors de travaux de réparation et de maintenance sur l’installation,la vanne ne doit pas être ouverte et la connexion des conducteursde protection ne doit pas être interrompue !

français

43

PTB 00 ATEX 2129 X
Accessoires

10.

ACCESSOIRES

11.

10.1.

Consignes de sécurité

TRANSPORT, STOCKAGE,ÉLIMINATIONREMARQUE !

ATTENTION !

Dommages dus au transport !

Risque de blessures, de dommages matériels dus à de mauvaises pièces !
De mauvais accessoires ou des pièces de rechange inadaptées
peuvent provoquer des blessures et endommager l’appareil ou
son environnement.
• Utiliser uniquement des accessoires et des pièces de rechanged’origine de la société Bürkert.

Les appareils insuffisamment protégés peuvent être endommagés
pendant le transport.

Dans la version des appareils avec boîte à bornes, le fusible du type1058 homologué PTB 01 ATEX 2064 U peut être utilisé dans la classede température T4.

Un mauvais stockage peut endommager l’appareil.

Fusible Type
1058

N° de
commande

Fusible Type
1058

N° de
commande

0,063 A

153 7170,500 A

153 735

0,080 A

153 745

0,630 A

153 736

0,100 A

153 7180,800 A

153 737

0,125 A

153 719

1,000 A

153 738

0,160 A

153 720

1,250 A

153 7390,200 A

153 7311,600 A

153 746

0,315 A

153 733

2,000 A

153 740

0,400 A

153 734

3,150 A

153 74244• Transportez l’appareil à l’abri de l’humidité et des impuretés etdans un emballage résistant aux chocs.
• Evitez le dépassement vers le haut ou le bas de la températurede stockage admissible.

• Stockez l’appareil au sec et à l’abri des poussières !
• Température de stockage : -40 … +55 °C.
Dommages à l’environnement causés par des pièces d’appareil contaminées par des fluides.
• Eliminez l’appareil et l’emballage dans le respect de l’environnement !
• Respectez les prescriptions en matière d’élimination desdéchets et de protection de l’environnement en vigueur.

françaiswww.burkert.com