Clean System Equipment

Support CE Marking

Equipment Use

ULTRA THIN FAN FILTER UNITE(PFT-CE)

Features（1）Compliant with CE marking *1. The compatible directives *2 are as follows.
▪Machinery Directive (2006/42/EC): Mechanical safety▪EMC Directive (2014/30/EU): Electromagnetic compatibility（2）This product can be installed in a narrow place.
（3）Air ﬂow control and operating status output (pulse output) functions as standard, and optimal forincorporation into various types of equipment.
*1: This device is for mounting onto machinery, and is compliant with CE marking while receiving power supply from the host machine.
When using the PFT-CE on its own, note that it is not compliant with CE marking.
*2: The Low Voltage Directive (2014/35/EU) is not within the applicable scope.
▪Applicable scope of the Low Voltage Directive: 50 −1,000 V AC, 75 −1,500 V DC
▪Power of the super-thin fan ﬁlter unit (PFT-CE): 24 V DC

Application
Semiconductor / liquid crystal manufacturing equipment, Inspection equipment, etc.

ULTRA THIN FAN FILTER UNITE
Clean System Equipment

Description of TypePET−CE−0606S−15LPre-ﬁlter
L: NonePower
5: 24 V DC
Main ﬁlter
1: HEPA 2: ULPA 3: Ultra ULPA
Casing material
S: SUS430
Size: Length x Width
Indicated in steps of 100 mm (fractions less than 100 mm to be rounded oﬀ)

Example: 610 x 610 → 0606

Product symbol
Support CE Marking

Standard Speciﬁcations
ModuleModel
Width
LengthDepthOuterdimensions

610×610
PFT-CE0606S-15L
610mm
610mm
152mm

HEPA
Grade
FilterComposition

CasingBlowerLow organic,
low-boron

610×1220

PFT-CEPFT-CE-0606
PFT-CE0612S-15L
S-25L
0606S-35L
610mm
610mm
1220mm
610mm
152mm
167mm
SUS430
Axial ﬂow fan, 1 unit
ULPA
Ultra ULPA
HEPA
Low organic,
low-boron

Boron-free

Low organic,
low-boron

PFT-CE0612S-35L

PFT-CE0612S-35L

610mm
1220mm
167mm
Axial ﬂow fan, 2 units
ULPA
Low organic,
low-boron

Ultra ULPA
Boron-free

Particle
99.99% or
99.9995% or
99.99995% or
99.99% or
99.9995% or
99.99995% orcollection rate more (0.3µm, PSL) more (0.1µm, PSL) more (0.1µm, PSL) more (0.3µm, PSL) more (0.1µm, PSL) more (0.1µm, PSL)UL compliant product, with Faceguard
SpecAccessories
Fittings: 4 pcs.
20 m3/min. (variable)
10 m3/min. (variable)
Rated airﬂow
External static pressure
120Pa
100Pa150Pa
120Pa
100Pa150Pa
Power supply
24 V DC
Current value
Apporox. 6 AApporox. 12 A
WeightApporox.10 kg
Apporox.11 kg
Apporox.17 kg
Apporox.18 kg

Remarks(1) This device is for mounting onto machinery, and is compliant with CE marking while receiving power supply from thehost machine. The applicable directives are as follows.
(a) Machinery Directive (2006/42/EC)(b) EMC Directive (2014/30/EU)(2) The airﬂow can be controlled with an air ﬂow control knob located on the side of the main body.
(3) 2 pulses/rotation can be outputted according to the rotation frequency of the blower.

The catalog is subject to change without any prior notice.

Creating comfortable environments

NIPPON MUKI CO., LTD.

Head Office:Nissin Ueno Bldg., 5-1-5, Higashi-ueno, Taito-ku, Tokyo,110-0015, Japan Tel.+81-3-6860-7501
Tohoku Office:Sompo Japan Sendai K Y Bldg., 3-10-19, Chuo, Aoba-ku, Sendai, Miyagi, 980-0021, Japan Tel.+81-22-266-7531
Osaka Office:
GROZ-BECKERT Bldg., 4-6-16, Hirano-machi, Chuo-ku, Osaka, 541-0046, Japan Tel.+81-6-6201-3751
Chubu Office:Nagoya Joho Center Bldg., 2-2-17, Sakae, Naka-ku, Nagoya, Aichi, 460-0008, Japan Tel.+81-52-202-9911
Kyushu Office:ND Bldg., 1-4-1, Daimyo, Chuo-ku, Fukuoka City, 810-0041, Japan Tel.+81-92-715-1651
Hiroshima Office:Otemachi Center Bldg., 2-8-5, Otemachi, Naka-ku, Hiroshima, 730-0051, Japan Tel.+81-82-248-3920
NIPPON MUKI
（SUZHOU）CO., LTD.:
No.116 Changyang Street, SIP, Suzhou, 215126, China Tel.+86-521-6507-7780

2018.3.1000（OTM）NM1006-1