Heat-Resistant Air Filter

Heat-Resistant Air Filter

Features1.Heat resistance
The High temperature ﬁlters from 150℃ up to 500℃ are available.
The ﬁlter is designed with special heat resistant materials.
2.Various dimensions
Special size is available upon request.

Contents

Heat-Resistant Air Filter

1. Material

2

2. Model3
Temperature：℃

Model number
Usage

Type
Normal

Max.

HEPA

500 ℃

500

500

̶

̶
P4

350

400
（1h）

ATMV

400 ℃

ATMVC

P5

ATMCU

P6

Drying Process

ATMH

P8

Incinerator

ATMCH

P9

250 ℃

250

250

Page Semi HEPA Page

Medium

Page

GCW

P3

̶

̶

GCV

P7

̶

̶

̶

̶

̶

̶

ASTCH

P11

ASTE

P14

ASTCE

P14

Clean Oven

Exhaust Processing

ATMCH-SL P10
180 ℃

150

180
（1h）

ATME

P12

ATMCE

P13

＊Others preﬁlter：CKR（P15）DSH（P16）

3. Handling Manual

117

1.Material

Temperature

Heat-Resistant Air Filter

Frame

Model

Media

Separator

Glass ﬁber
Stainless steel
Stainless steel（surface-treated） with SUS gauze

GCW

Sealant

GasketGlass ﬁber

Fine glass ﬁber

・The ﬁlter is made of glass ﬁber and stainless steel. Gasket contains resin.
・Special glass ﬁber media with SUS gauze is used.
・Special treatment on the surface of the frame against high temperature is done.
・No silicone is used.

５００℃

ATMV
ATMVC
GCV

400℃

Stainless steel

Glass ﬁber
Stainless steel
with SUS gauze

Glass ﬁber

Fine glass ﬁber

・The ﬁlter is made of glass ﬁber and stainless steel. Gasket contains resin.
・Special glass ﬁber media with SUS gauze is used.
・No silicone is used.

400℃

ATMCU
ATMH
ATMCH
ASTCH

２５０℃

Stainless steel

Glass ﬁber

Stainless steel

Glass ﬁber

Aluminum alloy

Glass ﬁber+siliconeATMCH-SL

Fine glass ﬁber

ＰＴＦＥ
（Fine glass ﬁber）

Glass ﬁber

・Due to the glass ﬁber media and special separator, the ﬁlter can be used under the high temperature.
ATME
ATMCE
ASTE
ASTCE

１8０℃

Stainless steel

Glass ﬁber

Aluminum

Silicone

Silicone・The ﬁlter can be used under the high temperature as the heat resistant silicone resin is applied
to the sealant and gasket.

Others（CKR）
No.

Material no.

Frame

1
2
3

B10
C13
S99

Cardboard
Steel plate
Stainless steel

Holder
Inlet
Punched metal
Punched metal
Punched metal

OutletPunched metal
Mesh
Mesh

Note.
Normal temp. disposable
High temp. Heat･Chemical resistantMedia changeable

Other materials are also available.

Others
（DSH）
Model
DSH

Frame
Stainless steel

Media
Aromatic polyamide, Polyester

Other materials are also available.

Remarks : 1. Glass ﬁber media contains acrylic binder. Silicone and PTFE also be used as a material forheat resistance. Conﬁrm if the material is no problem for your application.
2. As low heat resistant material such as acrylic binder is used, smoke is generated.

2

2.ModelHeat-Resistant Air Filter

Atomos
500℃ heat-resistantSemi-HEPA ﬁlter GCW
Model number

GCW−□−□−L−F□

Strong point

Add Ｚ for special modelCollection eﬃciency

・Ultra heat-resistant ﬁlter for continuous operation
up to 500°
C.

L：90%

・Low particle generation at high temperature.

Shows frame depth
P：290mm
Q：150mm

・No silicone is used.

Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

GCW−31−P−L−F
GCW−17−Q−L−F

610×610×290
610×610×150

31
17Pressure drop（Pa）
InitialFinal

Collection
eﬃciency（%）

Weight
（kg）

245

90
at 0.5‐1μm

21
13

400

Materials and Temperature
Frame

Materials
Separator

Sealant

GasketStainless steel

Glass ﬁber

Fine glass ﬁber gasket

Media

Glass wool
Stainless steel（Surface processed）（Held with Wire gauze）

Dimension available
Ｄ
（mm）
290
150

H
（mm）
305〜760305〜760

Speciﬁcation
Air Volume vs. Collection Eﬃciency
Collection efﬁciency（%）

99

95

90

3

at 0.5〜1μm

40

60

80

100

Rated air volume（%）W（mm）
305〜760305〜915

Temperature（℃）
NormalMaximum
500

500

Heat-Resistant Air Filter

Atomos
400℃ heat-resistant
HEPA ﬁlter ATMV
Model number

ATMV−□−□−FS4□

Strong point

Add Ｚ for special model

・Ultra heat-resistant ﬁlter for continuous operation
up to 350°
C.

Shows frame depth
P：290mm
Q：150mm・Low particle generation at high temperature.
・No silicone is used.

Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATMV−6−P−FS4
ATMV−10−P−FS4
ATMV−4−Q−FS4
ATMV−7−Q−FS4

500×500×290
610×610×290
500×500×150
610×610×150

6
10
4
7

Pressure drop（Pa）
InitialFinal
245Collection
eﬃciency（%）

Weight（kg）

99.97
at 0.3μm

17
21
11
13

490

Materials and Temperature
Frame

Media

Stainless steel

Glass wool
（Held with Wire gauze）

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Fine glass ﬁber gasket

350

400
（1h）

Dimension available
Ｄ
（mm）
290
150

H
（mm）
305〜760305〜760W（mm）
305〜760305〜915

Speciﬁcation

Collection efﬁciency（%）

99.999at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.99

99.95

99.9
0.05 0.07

0.1

0.2

0.3

Particle Diameter（μm）

0.5

4

Heat-Resistant Air Filter

Atomos
400℃ high heat-resistant
HEPA ﬁlter ATMVC
Model number

ATMVC−□−□−FS4□

Strong point

Add Ｚ for special model

・Ultra heat-resistant ﬁlter for continuous operation
up to 350°
C

Shows frame depth
P：290mm
Q：150mm・Low particle generation at high temperature.

Rated air volume：See Standard spec.（ Z stands for special spec.）

・No silicone is used.

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATMVC−20−P−FS4
ATMVC−14−Q−FS4

610×610×290
610×610×150

20
14Pressure drop（Pa）
Initial
Final
≦300
500
≦350

Collection
eﬃciency（%）

Weight（kg）

99.99
at 0.3μm

26
15Materials and Temperature
Frame

Media

Stainless steel

Glass wool
（Held with Wire gauze）

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Fine glass ﬁber gasket

350

400（1h）

Dimension available
Ｄ
（mm）
290
150

H
（mm）
305〜762305〜762W（mm）
305〜610305〜915

Speciﬁcation

Collection efﬁciency（%）

99.9995

at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.995
99.99

99.95
99.9

99.5
0.07

0.1

0.2

0.3

0.5

Particle Diameter（μm）

Heat-Resistant Air Filter

Atomos
400℃ heat-resistant
HEPA ﬁlter ATMCU
Model number

ATMCU−□−□−FS4HR□

Strong point

Add Ｚ for special model・No silicone is used.

Shows frame depth
P：290mm
Q：150mm・Ultra heat-resistant ﬁlter for continuous operation
up to 350°
C.

Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

Rated facevelocity（m/s）

ATMCU−35−P−FS4HR
ATMCU−24−Q−FS4HR

610×610×290
610×610×150

35
24

1.8
1.2

Pressure drop（Pa）
Collection
eﬃciency（%）
Initial
Final
≦250

500

Weight
（kg）
22
13

99.99
at 0.3μm

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketStainless steel

Glass ﬁber

Stainless steel

Glass ﬁber

Fine glass ﬁber gasket

Dimension available
Ｄ
（mm）
290
150

Temperature（℃）
NormalMaximum
350

400
（1h）

Structure of the separator

H（mm）
150〜762
150〜762W（mm）
150〜760
150〜915

Speciﬁcation
Air Volume vs. Collection Eﬃciency： ATMCU-24-Q-FS4HR： ATMCU-35-P-FS4HR

Pressune drop（Pa）

1000

Solid line → The inﬂow side
Wavy line → The outﬂow side

700
500

Inﬂow side separator

Outﬂow side separator

400
300
200

100

10

20

30

40 50

70

Rated air volume（m3/min）

100

6

Heat-Resistant Air Filter

Atomos
400℃ heat-resistantSemi-HEPA ﬁlter GCV
Model number

GCV−□−□−L−FS4□

Strong point

Add Ｚ for special modelCollection eﬃciency

・Ultra heat-resistant ﬁlter for continuous operation
up to 350°
C.

L：90%

・Low particle generation at high temperature.

Shows frame depth
P：290mm
Q：150mm

・No silicone is used.

Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

GCV−31−P−L−FS4
GCV−17−Q−L−FS4

610×610×290
610×610×150

31
17Pressure drop（Pa）
InitialFinal

Collection
eﬃciency（%）

Weight
（kg）

245

90
at 0.5‐1μm

21
13

490

Materials and Temperature
Frame

Media

Stainless steel

Glass wool
（Held with Wire gauze）

Materials
Separator

Sealant

GasketStainless steel

Glass ﬁber

Fine glass ﬁber gasket

Dimension available
Ｄ
（mm）
290
150

H
（mm）
305〜760305〜760

Speciﬁcation
Air Volume vs. Collection Eﬃciency
Collection efﬁciency（%）

99

95

90

7

at 0.5〜1μm

40

60

80

100

Rated air volume（%）W（mm）
305〜760305〜915

Temperature（℃）
NormalMaximum
350

400
（1h）

Heat-Resistant Air Filter

Atomos
250℃ heat-resistance
HEPA ﬁlter ATMH
Model number

ATMH−□−□−FS4□
Add Ｚ for special modelShows frame depth
P：290mm
Q：150mm
Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATMH−7−P−FS4
ATMH−31−P−FS4
ATMH−39−P−FS4
ATMH−3−Q−FS4
ATMH−17−Q−FS4
ATMH−21−Q−FS4

300×300×290
610×610×290
610×760×290
300×300×150
610×610×150
610×760×150

7
31
39
3
17
21

Pressure drop（Pa）
InitialFinal

245Collection
eﬃciency（%）

Weight（kg）

99.97
at 0.3μm

6
21
27
4
12
15

490

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum alloy

Glass ﬁber + Silicone

PTFE

250

250

Dimension available
Ｄ
（mm）
290
150

H
（mm）
305〜760305〜760W（mm）
150〜1,000
150〜1,220

Speciﬁcation

Collection efﬁciency（%）

99.999at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.99

99.95

99.9
0.05 0.07

0.1

0.2

0.3

Particle Diameter（μm）

0.5

8

Heat-Resistant Air Filter

Atomos
250℃ heat-resistanthigh Capacity ATMCH Volume
HEPA ﬁlter
Model number

ATMCH−□−□−FS4□
Add Ｚ for special modelShows frame depth
P：290mm
Q：150mm
Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATMCH−41−P−FS4
ATMCH−28−Q−FS4

610×610×290
610×610×150

41
28

Pressure drop（Pa）
InitialFinal
249±20

Collection
eﬃciency（%）

Weight（kg）

99.97
at 0.3μm

23
13

498

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum alloy

Glass ﬁber + Silicone

PTFE

250

250

Dimension available
Ｄ
（mm）
290
150

H
（mm）
305〜610305〜610W（mm）
305〜760305〜760

Speciﬁcation

Collection efﬁciency（%）

99.9999

at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.99

99.95

99.9
0.05 0.07

0.1

0.2

0.3

Particle Diameter（μm）

0.5

Heat-Resistant Air Filter

Atomos
250℃ heat resistantlarge air volume type HEPA
(without any silicone)
Model number

ATMCH−□−□−SLS4□

Strong point

Add Ｚ for special model・No silicone is used.

Shows frame depth
P：290
（292）
mm
Q：150mm・Environmental friendly product as frame can bereused. Easy to disassemble and dispose after
use as no adhesive is applied.

Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATMCH−41−P−SLS4ATMCH−61−P−SLS4ATMCH−28−Q−SLS4

610×610×290
760×760×292
610×610×150

41
61
28

Pressure drop（Pa）
InitialFinal≦249Collection
eﬃciency（%）

Weight（kg）

99.97
at 0.3μm

25.0
33.0
13.5

498

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum alloy

Glass ﬁber

PTFE

250

Dimension available
Ｄ（mm）
290（292）
150

250

Application

H（mm）
305〜760305〜610

・For heat treatment of precision parts and drying
process of production equipment

W（mm）
305〜1,000
305〜760

・For the areas requiring clean environment underhigh temperature

Remark 1: For over 610mm high or 760mm wide, only 292mm depth is available.
Frame with reinforcement is to be used.

Speciﬁcation

Collection efﬁciency（%）

99.999at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.99

99.95

99.9
0.05 0.07

0.1

0.2

0.3

Particle Diameter（μm）

0.5

10

Heat-Resistant Air Filter

Astron250℃ heat-resistantmedium ﬁlter
ASTCH
Model number

ASTCH−□−□FS4□
Add Ｚ for special modelCollection eﬃciency
90：PSAM90％
60：PSAM60％※PSAM：Photo scattering accumulation method

Shows dimension.See Standard spec. Z stands for special spec.

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ASTCH−36−※FS4
ASTCH−56H−※FS4
ASTCH−56−※FS4
ASTCH−18−※FS4
ASTCH−28−※FS4

500×500×290
610×305×290
610×610×290
500×500×150
610×610×150

34.5
24.0
53.5
16.5
26.0

Pressure drop（Pa）
InitialFinal

Collection
eﬃciency（%）※=90：167※=60：137※=90：343※=60：294※90=90※60=60※=90：118※=60： 78※=90：245※=60：196

PSAM

Weight
（kg）
15
12
21
5
12

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum alloy

Glass ﬁber + Silicone

PTFE

250

Dimension available
Ｄ
（mm）
290
150

11

H
（mm）
150〜610150〜610W（mm）
305〜1,000
305〜1,000

250

Heat-Resistant Air Filter

Atomos
180℃ heat-resistant
HEPA ﬁlter ATME
Model number

ATME−□−□−ES4□
Add Ｚ for special modelShows frame depth
P：290mm
Q：150mm
Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATME−31−P−ES4
ATME−39−P−ES4
ATME−17−Q−ES4
ATME−21−Q−ES4

610×610×290
610×760×290
610×610×150
610×760×150

29.5
37.5
16.5
20.5

Pressure drop（Pa）
InitialFinal
245Collection
eﬃciency（%）

Weight（kg）

99.97
at 0.3μm

19
24
10
13

490

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum

Silicone

Silicone150

180（1h）

Dimension available
Ｄ
（mm）
290
150

H
（mm）
150〜760
150〜760W（mm）
150〜1,500
150〜1,500

Speciﬁcation

Collection efﬁciency（%）

99.999at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.99

99.95

99.9
0.05 0.07

0.1

0.2

0.3

Particle Diameter（μm）

0.5

12

Heat-Resistant Air Filter

Atomos
180℃ heat-resistant highcapacity HEPA ﬁlter ATMCE
Model number

ATMCE−□−□−ES4□
Add Ｚ for special modelShows frame depth
P：290mm
Q：150mm
Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ATMCE−41−P−ES4
ATMCE−51−P−ES4
ATMCE−28−Q−ES4
ATMCE−34−Q−ES4
ATMCE−50−P−ETS4
ATMCE−62−P−ETS4

610×610×290
610×760×290
610×610×150
610×760×150
610×610×290
610×760×290

39.5
50.0
27.0
34.0
48.0
61.0

Air Volume TypeHigh capacity１High capacity２

Pressure drop（Pa）
Initial
Final
249

498

249±20498

Collection
eﬃciency（%）

Weight（kg）

99.97
at 0.3μm

21
26
12
14
19
24

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum

Silicone

Silicone150

180（1h）

Dimension available
Ｄ
（mm）
290
150

W
（mm）
150〜1,500
150〜1,500

H（mm）
150〜760
150〜760

Speciﬁcation

Collection efﬁciency（%）

99.99913

at 0.3μm

99.99

99.9

40

60

80

100

Rated air volume（%）

Particle Diameter vs. Collection Eﬃciency
Collection efﬁciency at rated cap（%）

Air Volume vs. Collection Eﬃciency

120

99.99

99.95

99.9
0.05 0.07

0.1

0.2

0.3

Particle Diameter（μm）

0.5

Heat-Resistant Air Filter

Astron180℃ heat-resistantmedium ﬁlter
Model number

ASTE−□−□ES4□
Add Ｚ for special modelCollection eﬃciency
90：PSAM90％
60：PSAM60％※PSAM：Photo scattering accumulation method

Rated air volume：See Standard spec.（ Z stands for special spec.）

ASTCE−□−□ES4□（High capacity type）

Add Ｚ for special modelCollection eﬃciency
95：PSAM90％
60：PSAM60％※PSAM：Photo scattering accumulation method

Rated air volume：See Standard spec.（ Z stands for special spec.）

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ASTE−36−※ES4
ASTE−56H−※ES4
ASTE−56−※ES4
ASTE−18−※ES4
ASTE−28−※ES4

500×500×290
610×305×290
610×610×290
500×500×150
610×610×150

34.5
24.0
53.5
16.5
26.0

Model

Dimension（mm）
H×W×D

Rated air volume（m3/min）

ASTCE−36−※ES4
ASTCE−56H−※ES4
ASTCE−56−※ES4
ASTCE−18−※ES4
ASTCE−28−※ES4

500×500×290
610×305×290
610×610×290
500×500×150
610×610×150

34.5
24.0
53.5
16.5
26.0

Pressure drop（Pa）
InitialFinal

Collection
eﬃciency（%）※=90：123※=60： 78※=90：255※=60：157※90=90※60=60※=90： 78※=60： 39※=90：157※=60： 48

PSAM

Pressure drop（Pa）
InitialFinal

Collection
eﬃciency（%）※=95：167※=60：137※=95：343※=60：294※95=90〜95※60=60〜65※=95：118※=60： 78※=95：196※=60：118

PSAM

Weight
（kg）
11
10
16
6
8
Weight
（kg）
13
11
19
8
10

Materials and Temperature
Frame

Media

Materials
Separator

Sealant

GasketTemperature（℃）
NormalMaximum

Stainless steel

Glass ﬁber

Aluminum

Silicone

Silicone

150

180
（1h）

Dimension available
Ｄ
（mm）
290
150

H
（mm）
150〜610150〜610W（mm）
150〜1,220
150〜1,220

14

Heat-Resistant Air Filter

CKR Filter（Heat resistant preﬁlter）

Model number

CKR□□
Material No.
Media No.

Media spec.（sample）
No.

Media No.

Dimension（mm）
H×W×D

1
2

CKR080CKR040500×500×50
500×500×50

Rated air volume（m3/min）Initial pressure drop（Pa）

1.5m/sec
18
18

1.5m/sec
157
314

2.5m/sec
30
30

2.5m/sec
343
627

Collection eﬃciency（Colorimetric）
1.5m/sec
54
63

2.5m/sec
55
72

Materials
HolderNo.

Material no.

Frame

1
2
3

B10
C13
S99

Cardboard
Steel plate
Stainless steel

Inlet
Punched metal
Punched metal
Punched metal

Note.

OutletPunched metal
Mesh
Mesh

Normal temp. disposable
・Heat resistant ・Chemical resistant・Media is replaceable

Other materials are also avairable.

Dimension available
H（mm）

No.

Item

1
2

CKR080CKR040Standard
500
500

W（mm）
Max
1000
1000

＊1 25mm thickness is also available.

Speciﬁcation
Air Volume vs. Pressure drop（Sample）： CKR080： CKR040

Pressune drop（Pa）

1000

500

200

100

15

10

20

30

50

Air volume（m3/min）

100Standard
500
500

Max
1000
1000

Thickness（mm）＊1
Standard
50
50

Heat-Resistant Air Filter

DSH Filter（Heat resistant preﬁlter）

Model number

DSH−□−□−M
M：Shows only the ﬁlter material
Rated air volume：See Standard spec.
（ Z stands for special spec.）
Material No.

Standard speciﬁcation
Model

Dimension（mm）
H×W×D

Rated facevelocity（m/s）

DSH−200−22−M
DSH−200H−22−M

500×500×20
500×500×20

1.0

Pressure drop（Pa）
InitialFinal
45

Collection
eﬃciency（%）

Weight
（kg）

90

0.2
0.2

294

Materials and Temperature
Model
DSH−200−22−M
DSH−200H−22−M

Media
Aromatic polyamide, Polyester

Temperature（℃）
180240Noncombustibility○○

Speciﬁcation
Rated face velocity vs. Pressure drop（Sample）： DSH-200： DSH-200H

Pressune drop（Pa）

100

50

10

0.1

0.5

1.0

Rated face velocity（m/s）

2.0

16

3.Handling ManualHeat-Resistant Air Filter

1. Introduction for pre-heatingHigh temperature resistant HEPA ﬁlter is designed to be used under the high temperature environment.
This type of ﬁlter is made of heat resistant materials. However, some materials are carbonized.（＊）
Please pre-heat before using ﬁlter.
＊ Note： Materials to be carbonized：（a）Acrylic binder and water repellent with ﬂuorine（mass ratio of 5%）
White smoke is generated when material starts being carbonized at 150℃.
（b）Binder with ﬁne glass ﬁber gasket：
White smoke is generated when material starts being carbonized at 150℃.
（c）PTFE gasket and tape to hold ﬁne glass ﬁber gasket：
Gasket starts being carbonized at 150℃ but tapes are hardly scattered as it is held by ﬁlter frame and gasket.
（1）Pre-heating is required at the highest temperature（in actual use）for 1 hour.
＊Do not pre-heat the ﬁlter over the temperatures stated on technical drawing.
＊If the maximum temperature is not stated on technical drawing, refer to the table below.
Sealant

White-colored Silicon（ATM（C）E, AST（C）
E）

Black-colored Silicon（ATM（C）
H, ASTCH）

Max. Temperature

180℃

250℃

Glass Fiber（ATMV, ATMVC,
ATMCU, GCV）

（GCW）

400℃

500℃

（2）Please pre-heat at site even if it is done at our factory.
（3）Increase temperature gradually at 10℃/min or lower.
（4）Extend time for pre-heating if white smoke is still generated.
（5）Handle with care as the ﬁlter media weakens after pre-heating.

2. In transportation（1）Handle carton box as instructed. Hold up carton box with both hands. Do not carry it on the shoulder.
（2）Unload carton box gently as frame and ﬁlter media are easily damaged.
Open carton box to check damage on if dropped.
（3）Load carton box vertically only. Maximum 3 cartons can be piled up.
（4）Avoid having carton box wet and vibration in transportation.

3. In storage（1）Do not put the carton box directly on a ﬂoor. Use pallet to make space. between carton box and ﬂoor.
（2）Store in a warehouse with no roof leaks and good ventilation.
（3）Load carton box vertically only. Up to 3 cartons can be put upon.
Store ﬁlter as originally packed. Repack ﬁlter with plastic bag inside carton box.

4. In installation（1）To avoid damage on ﬁlter, open the carton ﬁrst, put it upside down on the ground and then pull up the carton only.
（2）Wear gloves when handling ﬁlter and do not touch it by naked hands.
Grease or ﬁngerprint may cause stain at high temperature.
（3）Do not touch media and hold frame only to handle ﬁlter.
（4）Never step on ﬁlter as it is easily damaged.
（5）When setting a ﬁlter on horizonal chamber, install the ﬁlter with the peak of folding at 90degrees to the ground.
（6）When setting a ﬁlter on vertical chamber, use HR labeled ﬁlter.
（7）Install ﬁlter with airﬂow direction shown on the label.
（8）Install ﬁlter ﬁrmly.
（9）Fine glass ﬁber gaskets are not put on the ﬁlter because it is easy to be broken. Please put the gaskets on
the ﬁlter at user's site.

17

Heat-Resistant Air Filter
5. In use
（1）Record initial pressure drop just after installation.
（2）Use at or under the rated air volume. Keep a stright air ﬂow. The ﬁlter might be damaged if strong air blow hits
certain point even through using at or under the rated air volume.
（3）Pre-heating is required upon installation.
（4）White smoke might be generated when the temperature is increased, even after pre-heating.
（5）After pre-heating, ﬁlter media becomes weaker due to carbonization of binder. Handle with care.
（6）When the ﬁlter is temporary removed or replaced with new ﬁlter, use new gasket.
（7）Turn on/oﬀ airﬂow gradually as particle might be generated when fan is turned on/oﬀ.
（8）When the temperature is going up or down, particle might be generated from the material. Temperature
control should be done gradually. Use at a constant temperature as much as possible.
（9）Fine glass ﬁber that cannot be measured by particle counter might be generated when using the ﬁlter.
（10）Replace the ﬁlter when it reaches to the ﬁnal pressure drop.
（11）Lifetime of the material depends on the environment on site. If the drop of collection eﬃciency or any otherproblem are found, replace the ﬁlter.
（12）When it is used in special environment, contact us.

6．Direction to dispose ﬁlter.
（1）Discard ﬁlter as industrial waste.

18

Heat-Resistant Air Filter

This catalog is subject to change without any prior notice

NIPPON MUKI CO., LTD.
Head OfficeNissin Ueno Bldg., 5-1-5, Higashi-ueno, Taito-ku, Tokyo,110-0015, Japan Tel.+81-3-6860-7501
Tohoku Office
Sompo Japan Sendai K Y Bldg., 3-10-19, Chuo, Aoba-ku, Sendai, Miyagi, 980-0021, Japan Tel.+81-22-266-7531
Osaka Office
OX Yodoyabashi Bldg., 4-4-9, Fushimi-cho, Chuo-ku, Osaka, 541-0044, Japan Tel.+81-6-6201-3751
Chubu Office
Nagoya Joho Center Bldg., 2-2-17, Sakae, Naka-ku, Nagoya, Aichi, 460-0008, Japan Tel.+81-52-202-9911
Kyushu Office
ND Bldg., 1-4-1, Daimyo, Chuo-ku, Fukuoka City, 810-0041, Japan Tel.+81-92-715-1651
Hiroshima Office
GOJINSHA Hiroshima Otemachi Bldg., 2-8-5, Otemachi, Naka-ku, Hiroshima, 730-0051, Japan Tel.+81-82-248-3920

2015.9.1000（OTM）NM 010-3