DATA SHEETType 8652

AirLINE – the valve island optimised for process
automation• Safety-related shut-off of valves possible• Higher plant availability with PROFINET S2 (system redundancy)• Process reliability through pneumatic functions• Optimised for installation at the bottom of the control cabinet• EX-Versions: ATEX / IECEx Zone 2, cURus Haz. Loc. CL I, II, III Div 2

Product variants described in the data sheet may differ from the product presentation and description.

Can be combined withType ME43

Type description


Fieldbus gateway﻿﻿﻿Type 2012
Pneumatically operated
2/2-way globe valve
﻿ CLASSIC

﻿Type 8695

Control head for decentralised automation of ELEMENT
﻿ process valves

Type 8920
Bürkert Communicator



﻿

﻿


﻿

Type 8653
AirLINE Field – the valve
island – optimised for﻿ process automation

﻿Type 8614
Pneumatic control cabinet
solutions for hygienic
﻿ process environments
Type SV04
Spare part sets forType 8652

﻿

The valve island Type 8652 AirLINE has been especially developed for process
automation requirements. New diagnostic functions can be visualised on the
LC display, both in clear text as well as symbols. This makes it easy to relate to
the shown messages and helps to save time during start-up and maintenance.
Furthermore, the diagnostic message is also available at the controller. This, therefore, enables a fast overview of the plant status. The hardware is optimised for
installation at the bottom of the control cabinet. Installation on a standard rail is, ofcourse, also possible. Moreover, key pneumatic functions ensure increased processreliability. For instance, check valves in the exhaust air ducts make sure there is no
unplanned actuation due to pressure peaks.

﻿Standard | EU | en | 2024 - 08 - 20 | 15
© Christian Bürkert GmbH & Co. KG, Subject to alteration

Visit product website Type 8652

Table of contents
1.

General technical data
1.1..
1.2..

General data.............................................................................................................................................................................................................3
AirLINE Quick............................................................................................................................................................................................................5

2. Circuit functions
2.1..
2.2..

5.

7.

9.5..
9.6..
9.7..
9.8..

17

Bürkert Communicator Software........................................................................................................................................................................ 17

9. Ordering information
9.1..
9.2..
9.3..
9.4..

13

Product assembly..................................................................................................................................................................................................13
Electronic module with digital inputs (optional)...............................................................................................................................................14
Valves Type 6534 for safety-related shut-off, SIA variant (optional).......................................................................................................... 15
Module-based safety shutdown (optional).......................................................................................................................................................16
Example configuration..........................................................................................................................................................................................16

8. Product accessories
8.1..

12

Installation notes.................................................................................................................................................................................................... 12
Installation situation of the valve terminal inside the control cabinet.......................................................................................................... 12

Product design and assembly
7.1..
7.2..
7.3..
7.4..
7.5..

10

Power supply for communication and display..................................................................................................................................................10
Power supply for pneumatic valves....................................................................................................................................................................10
Fieldbus interface...................................................................................................................................................................................................11

6. Product installation
6.1..

8

Version 4-, 8- and 12-fold......................................................................................................................................................................................8
Version 16-, 20- and 24-fold.................................................................................................................................................................................9

Device/Process connections
5.1..
5.2..
5.3..

7

General notes...........................................................................................................................................................................................................7
Conformity................................................................................................................................................................................................................7
Standards..................................................................................................................................................................................................................7
Explosion protection................................................................................................................................................................................................7
North America (USA/Canada)...............................................................................................................................................................................7

4. Dimensions
4.1..
4.2..

6

Standard functions..................................................................................................................................................................................................6
SIA variant.................................................................................................................................................................................................................6

3. Approvals and conformities
3.1..
3.2..
3.3..
3.4..
3.5..

3

18

Bürkert eShop........................................................................................................................................................................................................18
Bürkert configurator..............................................................................................................................................................................................18
Bürkert product filter.............................................................................................................................................................................................18
Ordering chart replacement valves....................................................................................................................................................................19
Solenoid valve Type 6534....................................................................................................................................................................................19
Solenoid valve Type 6534 SIA variant (2nd port for shutdown)...................................................................................................................20
Electronic module.................................................................................................................................................................................................. 21
Connector module................................................................................................................................................................................................. 21
Plug – power supply.............................................................................................................................................................................................. 21
Ordering chart accessories..................................................................................................................................................................................22
Fieldbus gateway Type ME43.............................................................................................................................................................................22
Accessory for Software Bürkert Communicator..............................................................................................................................................22

Visit product website 

2 | 22

Type 8652

1.

General technical data

1.1.

General data

Product properties
Dimensions
Material
Body
Seal
Maximum installation width of avalve island
Width per station
Manual override
Number of valve positions
Maximum number of valve functions
Circuit functions/Operating principle 1.)
Pneumatic intermediate supply
Performance data
Pressure data
Pressure range
External supply air (auxiliary pilot air)Flow rate QNn value air

Flow rate QNn value air with integrated
P shut-off
Nominal operating mode
Switching time
Electrical data
Operating voltage
Voltage tolerance
Residual ripple (at DC)
Nominal power of each valve
Nominal current of each valve
Position feedback
Protection class
Total current
With fieldbus connection
Medium data
Operating medium
Compressed air quality
Approvals and conformities
Degree of protection
Explosion protection
North America (USA/Canada)Type Rating (NEMA 250, UL50/50E)

Further information can be found in chapter “4. Dimensions” on page 8.
PA (polyamide)
NBR and PUR
Further information can be found in chapter “4. Dimensions” on page 8.
11 mm
Latching, spring return (optional: lockable)
Max. 24
Max. 48
Further information can be found in chapter “2. Circuit functions” on page 6.
For versions with 16, 20 and 24 valve positions
Overpressure to atmospheric pressure
Vac.…10 bar
3…10 bar
310 l/min 1.) measured at + 20 °C, 6 bar pressure bar at valve inlet and 1 bar differential pressure
Flow reduced by approx. 10 %Continuous operation (100 % duty cycle)
Measured according to ISO 12238
24 V DC± 10 %
1 Vss
0.7 W (0.175 W after power reduction)
29 mA (10 mA after power reduction)
Max. 48
III according to DIN EN 61140, VDE 0140
Further information can be found in the operating instructions Type 8652 Oil-free or lubricated compressed dry air, neutral gases (5 μm filter recommended)
ISO 8573 - 1:2010, Class 7.4.4
IP20, IP65 in closed control cabinets
Further information can be found in chapter “3.4. Explosion protection” on page 7.
Further information can be found in chapter “3.5. North America (USA/Canada)” on page 7.
Type 4X in closed enclosures (8652 with stainless steel version)

Process/Port connection & communication
Working port
D 6, D ¼
Air supply connection
D 10, D ⅜
Communication module
ME43
Communication interface
PROFIBUS DP
Industrial Ethernet (PROFINET IO, EtherNet/IP, Modbus TCP, EtherCAT,
CC-Link IE Field Basic)
PROFINET S2
CANopenbüS (for networking with Bürkert devices)
Environment and installation
Installation position
Any
Storage temperature- 20…+ 60 °C
Ambient temperature- 10…+ 55 °C

Visit product website 

3 | 22

Type 8652

Accessories
Bürkert Software 2.)

Bürkert Communicator Software
Further information can be found in chapter “8.1. Bürkert Communicator Software” on page 17.

1.) The maximum flow rate depends on the valve function.
2.) For commissioning, the Bürkert Communicator software Type 8920  as well as the associated USB büS interface set 1 with Article no. 772426  are required.

Visit product website 

4 | 22

Type 8652

1.2.

AirLINE Quick

Note:
The valves of Type 0460 valves cannot be installed with AirLINE Quick due to their size.
AirLINE Quick considerably reduces the use of components in the control cabinet. With the AirLINE Quick Adapter, the valve terminal isadapted directly to the control cabinet floor or control cabinet wall.
Advantages:• Reduced space requirement in the control cabinet• This makes it possible to use more compact control cabinets• Reduced installation effort due to hose connections directly at the bottom of the control cabinet
Product properties
Material
AirLINE Quick Adapter

Stainless steel 1.4301
Anodised aluminium
Pneumatic connection
Stainless steel 1.4301
Nickel-plated brass
Valve functions per station
8, 16, 24, 32, 40 and 48
Process/Port connection & communication
Connection
Pneumatic feeding
Pneumatic service ports
Environment and installation
Installation position

D 10, D ⅜"
Plug-in coupling Ø 6 mm, Ø ¼"
Control cabinet wall
Control cabinet floor

AirLINE Quick Adapter in stainless steel 1.4301 or anodised aluminium

Valve with 11 mm width/station
Valve functions per station Type 8652:
8, 16, 24, 32, 40 and 48
Pneumatic connections
Supply / Disposal:– D 10– D ⅜"
Pneumatic connections:– Stainless steel 1.4301– Nickel-plated brass

Visit product website 

Pneumatic connections:– Push-in 6 mm
– D ¼"

5 | 22

Type 8652

2.

Circuit functions

2.1.

Standard functions

SymbolDescription
2

12

14

1

3

1

2

12

14

3

4

2

5 1 3
4

5
4

14

1

14

4

1

5

12

2

4

Circuit function L (CF L)
5/3-way solenoid valve
With manual override
In middle position all ports locked

122

Circuit function M (CF M)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 ventilated

12

5 13
4

14

2

Circuit function N (CF N)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4 exhausted

12

5 13
4

14

2

Circuit function Z (CF Z)
5/2-way solenoid valve
Impulse version with 2 coils and manual override
Pressure applied via port (1), therefore one of the two ports (2) or (4) is under pressure.

12

5 1 3

2.2.

SIA variant

SymbolDescription
2

12
1

14

4

4

1

5

Circuit function C (CF C)
2 x 3/2-way solenoid valve
Servo-controlled
Normally closed
Circuit function H (CF H)
5/2-way solenoid valve
Servo-controlled
Pressure applied via port (1), therefore one of the two ports (2) or (4) is under pressure.

2

2

4

14
3

5 1 3

14

Circuit function D (CF D)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally open
Circuit function H (CF H)
5/2-way solenoid valve
Servo-controlled, with manual override
Pressure applied via port (1), therefore one of the two ports (2) or (4) is under pressure.

5 13

14

Circuit function C (CF C)
2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally closed

12

12

5 13

Visit product website 

Circuit function L (CF L)
5/3-way solenoid valve
In middle position all ports locked

6 | 22

Type 8652

3.

Approvals and conformities

3.1.

General notes• The approvals and conformities listed below must be stated when making enquiries. This is the only way to ensure that the productcomplies with all required specifications.
• Not all available versions can be supplied with the below mentioned approvals or conformities.

3.2.

Conformity

In accordance with the Declaration of Conformity, the product is compliant with the EU Directives.
Type Rating (NEMA 250, UL50/50E): Type 4X in closed enclosures (8652 with stainless steel version)

3.3.

Standards

The applied standards which are used to demonstrate compliance with the EU Directives are listed in the EU-Type Examination Certificate
and/or the EU Declaration of Conformity.

3.4.

Explosion protection

Approval

Description
Optional: Explosion protection
As a category 3 device suitable for zone 2/22.
ATEX:
BVS 20 ATEX E 031 U
II 3G Ex ec IIC Gc
II 3D Ex tc IIIC Dc
IECEx:
IECEx BVS 20.0024 U
Ex ec IIC Gc
Ex tc IIIC Dc

3.5.

North America (USA/Canada)

Approval

Description
Optional: UL Listed for the USA and Canada
The products are UL Listed for the USA and Canada according to:• UL 61010‑1 (ELECTRICAL EQUIPMENT FOR MEASUREMENT, CONTROL, AND LABORATORY USE – Part 1: General
Requirements)• CAN/CSA-C22.2 No. 61010‑1• UL50/50E (Enclosure Type 4X)
Optional: UL Recognized for the USA and Canada for Hazardous Locations – Explosion protection
The products are UL Recognized for Hazardous Locations for the USA and Canada according to:Class I, Zone 2, AEx ec IIC Gc/ Ex ec IIC Gc U
Class II, Zone 22, AEx tc IIIC Dc/ Ex tc IIIC Dc U
Class I, Division 2, Group A, B, C, D/ Class II, III, Division 2, Group F, G

Visit product website 

7 | 22

Type 8652

4.

Dimensions

4.1.

Version 4-, 8- and 12-foldNote:Dimensions in mm, unless otherwise statedB
A

optional tube connection ø 10 mm, ø ⅜"

89

37.25

C

Venting connection for auxiliary control air
optional tube connection ø 6 mm, ø ¼"

optional tube connection
ø 10 mm, ø ⅜"

16.6
31.75

optional tube connection ø 6 mm, ø ¼"

11m x 11

16.6

Supply port for auxiliary control air
optional tube connection ø 6 mm, ø ¼"

9.8

101.05117.7 + (n x 44)
84.2 + (n x 44)
64.15
44
15.9

104.7

ca. 22
ca. 19

18.5

35.55

45.5

5

29

optional tube connection
ø 6 mm, ø ¼"

67.5

170

standard rail EN 50022 35 x 7.5 or 35 x 15

69.2
50.2

B

optional tube connection ø 10 mm, ø ⅜"

Version4-fold8-fold12-fold

Visit product website 

A
66
37
77

B
–
111
154

C
4 x M58 x M510 x M5

m
3
7
11

n
1
2
3

8 | 22

Type 8652

4.2.

Version 16-, 20- and 24-foldNote:Dimensions in mm, unless otherwise stated
B

B
A

C

89

37.25

16.6
31.75

15.9

Version16-fold
20-fold
24-fold

11
m' x 1111
m x 11
C

64.15

A
112
134
156

Visit product website 

44

144 + (n x 44)
110.5 + (n x 44)
D
9.8

B
224
268
312

C
10 x M5
10 x M5
10 x M5

D
114.3
158.3
158.3

m
7
11
11

m‘
7
7
11

n
4
5
6

9 | 22

Type 8652

5.

Device/Process connections

5.1.

Power supply for communication and display

Note:• Connect 5-pin spring-loaded terminal according to the pin assignment.
• Possible cable cross-section: ≤ 1.5 mm2• See “9.7. Plug – power supply” on page 21
Spring-loaded terminal 5-pin

5.2.

ColourAssignment

Red
White
Green
Blue
Black

24 V DCCAN_H (büS connection)
SHIELDINGCAN_L (büS connection)
GND

Power supply for pneumatic valves

Note:• The interface plate has a 2-pin spring-loaded terminal to which the pneumatic valves’ power supply is connected.
• See “9.7. Plug – power supply” on page 21
Spring-loaded terminal 2-pin
1

Clip

ColourAssignment

1
2

Red
Black

AUX 24 V
GND

2Visit product website 

10 | 22

Type 8652

5.3.

Fieldbus interface

Note:
CANopen requires 2 terminating resistors: one at the beginning of the network and one at the end. An indicator of the correct bus scheduling is the resistance between CAN_H and CAN_L when the power is switched off. This should be approx. 60 Ω.
CANopen/büS – Spring terminal 5-pin

8 Modbus TCP,
Industrial Ethernet (PROFINET I/O, EtherNet/IP,
7
EtherCAT, CC-Link IE Field Basic) or PROFINET
6 S2 – Interface X1
5and X2 RJ45
4
3
2
1

8
7
6
5
4
3
2
1

PROFIBUS DPV1 D-Sub 9 – D-Sub 9-pin female

6
7
8
9

1
2
3
4
5
6
7
8
9

Visit product website 

1
2
3
4
5

ColourAssignment

Red
White
Green
Blue
Black

24 V DCCAN_H (büS connection)
SHIELDINGCAN_L (büS connection)
GND

Pin

Assignment

1
2
3
4
5
6
7
8

TX+
TXRX+
N.C.
N.C.
RXN.C.
N.C.

Pin

Assignment

1
2
3
4
5
6
7
8
9

SHIELDING
M24 (optional)
RxD/TxD-P (B-line)
CNTR-P (optional)
DGND+ 5 V (supply for termination resistor)+ 24 V (optional)
RxD/TxD-N (A-line)
CNTR-N (optional)

11 | 22

Type 8652

6.

Product installation

6.1.

Installation notes

Installation situation of the valve terminal inside the control cabinet
To use the Hot Swap function, always observe a minimum distance to the front edge of the control cabinet when installing the valve island
inside the control cabinet. Please also refer to the detailed description in the operating instructions Type 8652 .

max. 25

Mounting platemin. 60.5

Z

max. 19.5

Distance from the control cabinet
rear wall to the mounting plate

Visit product website 

12 | 22

Type 8652

7.

Product design and assembly

7.1.

Product assemblyInterface plate 24V without modular shut-off
Interface plate 24V with modular shut-off

Electronic module
Electronic module with digital inputs

Complete supply manifold (Hot Swap)

Termination resistor
Fieldbus-Gateway ME43

Connection module without feed

Connection module withintegrated pressure sensor
Connection module with feed

Pneumatic valves
Adapter plate AirLINE Quick

Visit product website 

13 | 22

Type 8652

7.2.

Electronic module with digital inputs (optional)

The position feedbacks are supplied (24 V) by the electronic module. Current is limited to maximum 30 mA per position feedback. Standard
3-wire sensors and 2-wire sensors with voltages between 10…30 V as well as mechanical limit switches can be used.
Note:• Connect the position feedback indicator according to the pin assignment on the electronic module.
• Possible cable cross-section: ≤ 1.5 mm2• Maximum cable length: < 30 m

Mechanical limit switch
3-wire sensor

2-wire sensor

The following data may be displayed depending on the sensor used:
Possible data
Sensor actuatedSensor not actuated
Short circuit
Wire break

3-wire sensors

2-wire sensors
X
X
X
–

X
X
–
X

Mechanical limit switches
X
X––

8DI-Module (Digital input module)
Product properties
Diagnosis
Electrical data
Electrical version
Switching threshold
Input current of VON, typ. 24 V DC
Input impedance
Galvanic isolation

Visit product website Open-circuit detection with 2-wire sensors, short-circuit detection with 3-wire sensors
2-wire sensor, 3-wire sensor, mechanical limit switches
VOFF = 0…5 V
VON = 10…30 V
Max. 5.7 mA per channel> 4 KΩ
No, all channels have a common reference potential

14 | 22

Type 8652

7.3.

Valves Type 6534 for safety-related shut-off, SIA variant (optional)

Note:• Type 6534  valves are equipped with additional connection terminals. A valve circuit can therefore be interrupted by an external switch.
Manual override is not required for these valve variants. Technical data of Type 6534 valves, SIA variant correspond to standard device
data. To use the shut-off function, connect the terminal to a potential-free contact (mechanical switch or relay). The switching contact
must be located in the same control cabinet as the valve block. Line length must be limited to a maximum of 2 m.
• The valves Type 6534  can only be ordered as spare parts. For more information on the cable plug, see data sheet Type SV04 .
FeatureDescription
The yellow connection terminals are pluggable and can be removed
to facilitate connection of a cable. Except for CF H, there are always
2 connection terminals. To avoid mixing up the connections, theconnection terminals are coded.

CodingOn delivery, the connection terminals are provided with a bridge toensure the valve can be put into operation immediately. Remove thebridge before connecting a cable.

BridgeConnection terminals

Required switching capacity of the contact

Pluggable screw-type terminal, 2-pin, coded
wire cross-section (rigid or flexible) 0.14 mm²...1.5 mm²(AWG 28…16)
0.5 A / 24 V DC

Connection designation

Circuit diagram

12(+)
12

Electricalconnection valve
12 (+)

12(–)

24 V

14(+)

14(–)

Potential freecontact

Coil

Connection terminal
1212Connection terminal14

14

12 (–)
14 (+)24 V

14

14 (–)

Connection designation

Circuit diagram

Electricalconnection valve
14 (+)

14 (+)24 V
14 (–)

Visit product website Potential freecontact
Connection terminal
14

Coil

14

14 (–)
14

15 | 22

Type 8652

7.4.

Module-based safety shutdown (optional)

Connection designation

Optional:

Connections for module-based safety shutdown
Terminal 1 = valve unit 1, Terminal 2 = valve unit 2, ...

To use the switch-off function, connect the connection to a potential-free contact (mechanical switch or relay). The contact must be locatedin the same control cabinet as the valve terminal, but limit cable length to a maximum of 2 m.
Electrical data
Connection
Required switching capacity of the contact

7.5.

Pluggable spring-loaded terminal, 12-pin
Conductor cross-section (rigid or flexible) 0.14 mm²...1.5 mm² (AWG 26…16)
1.5 A / 24 V DC

Example configuration

The following illustration shows a network with the example of AirLINE Type 8652 with Industrial Ethernet version (PROFINET IO, EtherNet/IP,
Modbus TCP, EtherCAT, CC-Link IE Field Basic) as master valve terminal and various AirLINE Type 8652 with büS version as slave valve
terminals.
Industrial Ethernet
24 V DC, GND, CAN_L, CAN_H

Visit product website 

16 | 22

Type 8652

8.

Product accessories

8.1.

Bürkert Communicator Software

Note:
The corresponding communication software can be downloaded from the website Type 8920 .
The Bürkert Communicator is the most important software component of the EDIP (Efficient Device Integration Platform). Various features ofthis universal tool simplify the configuration and parametrisation of devices equipped with a digital CANopen-based interface. With this tool,
the user has a complete overview of cyclic process values as well as acyclic diagnostic data. The integrated graphical programming
environment enables the creation of decentralised sub-system control functions. The connection to the PC is established with a USB-CAN
adapter. The adapter is available as an accessory (see “9.8. Ordering chart accessories” on page 22 ).
The Bürkert Communicator enables:• Configuration, parametrisation and diagnosis of EDIP devices / networks• Easy and comfortable mapping of cyclic values• Graphical display of process values• Firmware update for the connected EDIP devices• Backup and restoring of device configurations

Visit product website 

17 | 22

Type 8652

9.

Ordering information

9.1.

Bürkert eShop
Bürkert eShop – Easy ordering and quick delivery
You want to find your desired Bürkert product or spare part quickly and order directly? Our
online shop is available for you 24/7. Sign up and enjoy all the benefits.
Order online now

﻿

9.2.

Bürkert configurator
Bürkert configurator – Configuring products easily
You want to put together a product that is precisely tailored to your needs in just a few
guided steps? Configure selected Bürkert products with our online configurator.
Configure product

9.3.

Bürkert product filter
Bürkert product filter – Get quickly to the right productYou want to select products comfortably based on your technical requirements?
Use the Bürkert product filter and find suitable articles for your application quickly and easily.
Try out our product filter

Visit product website 

18 | 22

Type 8652

9.4.

Ordering chart replacement valves

Solenoid valve Type 6534
Note:
Further information about this product version can be found in chapter “7.3. Valves Type 6534 for safety-related shut-off, SIA variant(optional)” on page 15.
Circuit function

C (CF C)2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally closed
2

12
1

3

1

2
1

4

3

1

Voltage/Frequency[mm][l/min][bar]

4

270 l/min4

Article no. 2.)
incl. screw

Vac....10 3.)
3…10

15

15

24 V DC301374 

310 l/minVac....10 3.)
3…10

15

15

24 V DC301375 

4

290 l/minVac....10 3.)
3…10

20

25

24 V DC301376 

4

290 l/minVac....10 3.)
3…10

20

25

24 V DC301377 

4

275 l/minVac....10 3.)
3…10

15

15

24 V DC

301380 

4300

Vac....10 3.)
3…10

20

20

24 V DC301379 [V/Hz]

5

2
12

Z (CF Z)
5/2-way solenoid valve
Impulse version with 2 coils and manual
override
Pressure applied via port (1), therefore
one of the two ports (2) or (4) is underpressure.
4

Switching times
Opening
Closing
[ms]
[ms]

4

14

5 1 3

14

Pressurerange

5

H (CF H)
5/2-way solenoid valve
Servo-controlled, with manual override
Pressure applied via port (1), therefore
one of the two ports (2) or (4) is underpressure.
14

QNn value 1.)
Air

4

14

D (CF D)2 x 3/2-way solenoid valve
Servo-controlled, with manual override
Normally open
12

Orifice

2

12

5 1 3

L (CF L)
5/3-way solenoid valve
With manual override
In middle position all ports locked
14

4

2

12

5 13

M (CF M)
5/3-way solenoid valve
With manual override
In middle position ports 2 and4 ventilated
14

4

2

12

5 13

Visit product website 

19 | 22

Type 8652

Circuit function

N (CF N)
5/3-way solenoid valve
With manual override
In middle position ports 2 and 4
exhausted4

142

Orifice

QNn value 1.)
Air

Pressurerange

Switching times
Opening
Closing[ms][ms]

Voltage/Frequency[mm][l/min]

[bar]

4

300

–

–

Article no. 2.)
incl. screw

Vac....10 3.)
3…10

20

20

24 V DC

301381 

–

–

–

–

335779 [V/Hz]

12

5 13

Dummy valve

1.) Approx. 3 % flow reduction for Hot Swap function
2.) The valves are components or spare parts of the Type 8652 Valve Terminal and can only be used on the Type 8652 Valve Terminal.
3.) Separate auxiliary pilot air min. 3 bar. Please observe the pilot pressure table in the operating instructions Type 8652 .

Solenoid valve Type 6534 SIA variant (2nd port for shutdown)
Note:
Further information about this product version can be found in chapter “7.3. Valves Type 6534 for safety-related shut-off, SIA variant(optional)” on page 15.
Circuit function

C (CF C)2 x 3/2-way solenoid valve
Servo-controlled
Normally closed
2

12
1

1

4

Voltage/Frequency[mm][l/min][bar]

4

270 l/min

4

4

Article no. 2.)
incl. screw

Vac....10 3.)
3…10

15

15

24 V DC338802 

290 l/minVac....10 3.)
3…10

20

25

24 V DC338805 

275 l/minVac....10 3.)
3…10

15

15

24 V DC

346830 [V/Hz]

12

L (CF L)
5/3-way solenoid valve
In middle position all ports locked
4

Switching times
Opening Closing
[ms]
[ms]

2

5 1 3

14

Pressurerange

5

H (CF H)
5/2-way solenoid valve
Servo-controlled
Pressure applied via port (1), therefore
one of the two ports (2) or (4) is underpressure.
14

QNn value 1.)
Air

4

14
3

Orifice

2

12

5 13
1.) Approx. 3 % flow reduction for Hot Swap function
2.) The valves are components or spare parts of the Type 8652 Valve Terminal and can only be used on the Type 8652 Valve Terminal.
3.) Separate auxiliary pilot air min. 3 bar. Please observe the pilot pressure table in the operating instructions Type 8652 .

Visit product website 

20 | 22

Type 8652

9.5.

Electronic module

Beschreibung
Electronics module with digital inputs
Electronics module without digital inputs

9.6.

Connector module

Beschreibung
Connection module without pressure sensor with additional connection for compressed air supply(Connection size: plug-in coupling Ø 6 mm and Ø 10 mm)
Connection module without pressure sensor with additional connection for compressed air supply(Connection size: plug-in coupling Ø ¼ mm and Ø ⅜ mm)
Connection module without pressure sensor without additional connection for compressed air supply
Connection module with pressure sensor, connection for compressed air supply: plug-in coupling Ø 6 mm and Ø 10 mm
Connection module with pressure sensor, connection for compressed air supply: plug-in coupling Ø ¼ mm and Ø ⅜ mm

9.7.

Article no.
384872 
384873 

Article no.
384863 
384864 
384866 
384867 384868 

Plug – power supply

Beschreibung
Spring-loaded terminal 5-pin

Article no.
920180 

Spring-loaded terminal 2-pin

920442 

Visit product website 

21 | 22

Type 8652

9.8.

Ordering chart accessories

Fieldbus gateway Type ME43
Note:
• Please note that the ME43 gateway modules are not configured ex works. However, these absolutely must be configured in order to be
used in a system. The device description files must be generated with the Bürkert Communicator software before the start-up of asystem.
• Further information can be found in the operating instructions Type ME43 .
Beschreibung
Fieldbus gateway Type ME43 – Industrial Ethernet (PROFINET, EtherNet/IP, Modbus TCP, EtherCAT®)
Fieldbus gateway Type ME43 – Profibus DP
Fieldbus gateway Type ME43 – CANopen/büS
Feldbus-Gateway Typ ME43 – PROFINET S2Article no.
301799 301803 301802 
20081296 

Accessory for Software Bürkert Communicator
Description
büS cable extension, M12, cable length: 0.1 m
büS cable extension, M12, cable length: 0.2 m
büS cable extension, M12, cable length: 0.5 m
büS cable extension, M12, cable length: 1 m
büS cable extension, M12, cable length: 3 m
büS socket, M12, straight, A-codedbüS plug, M12, straight, A-codedbüS socket, M12, angled, A-codedbüS plug, M12, angled, A-codedbüS Y plug
büS Y plug for linking 2 separately supplied segments of a büS network
Termination resistor (directly pluggable)
büS plug, M12, terminating resistor 120 Ω
büS socket, M12, terminating resistor 120 ΩPower supply unit Phoenix Class2 (Type 1573), 85…240 V AC/24 V DC, 1.25 A, NEC Class 2 (UL 1310)
Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 1 A, NEC Class 2 (UL 1310)
Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 2 A, NEC Class 2 (UL 1310)
Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 3.8 A, NEC Class 2 (UL60950 - 1)
Power supply unit for standard rail (Type 1573), 100…240 V AC/24 V DC, 10 A
microSD card
USB büS interface set 1 (Type 8923) for connection to the Bürkert Communicator software: includes connection cable(M12 and micro USB), stick with integrated terminating resistor, power supply and software
USB büS interface set 2 (Type 8923) for connection to the Bürkert Communicator software: including büS stick,connection cable to M12 plug, M12 connection cable on micro USB for the büS service interface and Y distributor,
cable length: 0.7 m
License for graphical programming (only required for a running time > 60 minutes)
Software Bürkert Communicator

Article no.
772492 
772402 
772403 
772404 
772405 
772416 
772417 
772418 
772419 
772420 
772421 
303833 
772424 
772425 
772438 
772361 
772362 772898 
772698 
774087 
772426 
772551 

567713 Type 8920 

1.) Due to lack of space, the M12 single connectors may not be suitable for their simultaneous use on the same side of the Y connector. Please use the available ready-made assembled
cable in this case.

Visit product website 

22 | 22