目
第１章
第１節

目次
総則

的

§1 目 的··················································································································1
第２節

ガイドラインの適用範囲§2 ガイドラインの適用範囲 ·························································································3
第３節

ガイドラインの構成§3 ガイドラインの構成 ·································································································4
第４節

用語の定義

§4 用語の定義 ·············································································································6

第２章
第１節

技術の概要と評価

技術の概要

§5

技術の目的 ··········································································································9§6技術の概要 ········································································································ 11§7技術の特徴 ········································································································ 14§8前段ろ過施設の概要と特徴 ··················································································· 19§9散水担体ろ床の概要と特徴 ··················································································· 21§10 最終ろ過施設の概要と特徴 ··················································································· 24§11 技術の適用条件 ·································································································· 26§12 導入シナリオ ····································································································· 28
第２節

実証研究に基づく評価の概要§13 技術の評価項目と評価方法 ··················································································· 31§14 技術の評価結果 ·································································································· 33

第３章
第１節

導入検討

導入検討手法§15 導入検討手順 ····································································································· 37§16 基礎調査 ··········································································································· 38§17 導入効果の検討·································································································· 39

§18 導入判断 ··········································································································· 44
第２節 導入効果の検討例 ···························································································· 45

第４章
第１節

計画・設計

導入計画

§19 計画の手順 ········································································································ 49§20 基本事項の把握 ·································································································· 51§21 水処理施設の容量計算 ························································································· 53§22 汚泥発生量の算定と汚泥処理能力の確認、一次濃縮分離水負荷の算定 ························· 54§23 施設配置の検討 ·································································································· 58§24 導入効果の検証 ·································································································· 60
第２節

施設設計

§25 本技術の施設設計の全体的な考え方 ······································································· 61
第３節

前段ろ過施設§26 施設構成 ··········································································································· 63§27 前段ろ過施設の設計 ···························································································· 64§28 既設改造の留意点 ······························································································· 69
第４節

散水担体ろ床§29 施設構成 ··········································································································· 71§30 散水担体ろ床の設計 ···························································································· 72§31 既設改造の留意点 ······························································································· 78§32 脱臭 ················································································································· 79
第５節

最終ろ過施設§33 最終ろ過施設の施設構成 ······················································································ 80§34 最終ろ過施設の設計 ···························································································· 81§35 既設改造の留意点 ······························································································· 84
第６節

一次濃縮施設§36 施設構成 ··········································································································· 85§37 一次濃縮施設の設計 ···························································································· 87§38 既設改造の留意点 ······························································································· 94

第７節

その他留意点§39 安全対策 ··········································································································· 95§40 環境対策 ··········································································································· 96§41 監視制御システム ······························································································· 97§42 汚泥処理施設への影響 ························································································· 99§43 災害対策 ········································································································· 101

第５章
第１節

維持管理

システム全体としての管理§44 導入システム全体としての維持管理 ····································································· 103

第２節

運転管理

§45 前段ろ過施設および一次濃縮槽施設 ····································································· 105§46 散水担体ろ床 ··································································································· 106§47 最終ろ過施設 ··································································································· 109§48 水質管理 ········································································································· 110§49 環境対策 ··········································································································111
第３節

保守点検

§50 保守点検 ········································································································· 113
第４節

異常時の対応と対策§51 異常時の対応と対策 ·························································································· 119

参 考 文 献資料編

１．実証研究結果 ........................................................................................................................... 124
２．ケーススタディ ....................................................................................................................... 158
３．海外等への適用の留意点 ........................................................................................................ 170
４．標準活性汚泥法の電力費、汚泥発生量（参考） .................................................................... 174
５．問い合わせ先 ........................................................................................................................... 177