Air Filters and Air-Conditioning Systems

General Catalog of Air-Conditioning Products
Air Filtration Products & Systems

Further,another step of progress.
Exert all one's powers.

Japan Vilene Company, Ltd. develops a broad range of air-conditioning
filters and equipment that help us live synergistically with the earth
and our environment.

Based on our technologies for developing
non woven fabrics,we have developed
comprehensive filtration systems to help
create a clean environment.
Since the 1960s, Japan Vilene Company, Ltd. has been allied with the
Freudenberg group Germany―a world-renown manufacturer of non
woven fabrics―and has been developing and marketing the "Viledon"
series of non woven air filter products. We have since expanded ourtechnologies into the realm of filtration systems, and are currently
focusing our energies in applications for generic air-conditioning aswell as in creating clean spaces in industrial air-conditioning applications.

1

CONTENTS
VILEDON AIR FILTER…… 3

PANEL FILTER…… 5

AUTOMATIC ROLL FILTER…… 5

Environment-friendly ﬁlter series
Rigid Filter【Element changeable】 …… 6
Rigid Filter【Box-shaped】…… 7
Rigid Filter【Prevent sea salt particle】…… 8
Pleated Filter…… 8
Pocket Filter…… 9
RIGID FILTER CASING SERIES …… 10
Filter installation frame…… 10

GAS REMOVAL FILTER…… 11

HEPA / ULPA FILTER
Filter installation frame

…… 12
…… 12

Special Applications
Anti-Viral Infection Filter■ VZ,

V ﬁlter

Anti-Pollen Air Shower…… 13■ V・AS-CB type…… 13

■ Easy-to-Install Air Shower…… 13

Asbestos removal work

■ Negative pressure dust remover …… 13● This is a general catalog for air-conditioning products marketed by Japan Vilene.
Please refer to individual product catalogs for more speciﬁc product information.
● If you do not have a product catalog, you can either download one from our web
site, or request one of our agents to have one mailed to you.

2

VILEDON AIR FILTERThe Viledon air ﬁlter is a high-quality air ﬁlter that is based on
non-woven fabric. Non-woven literally means "not woven."
This material was developed through a marriage of the idea behindpaper and felt production with state-of-the-art technologies, namelyorganic chemistry and polymer chemistry.
This allows us to combine synthetic ﬁbers and a variety of othermaterials, oﬀering great latitude in designing speciﬁc physical andchemical properties for speciﬁc applications.
Viledon air ﬁlters are made of materials that are highly ﬂexible inthis regard.

PA/305HL

PS/600N

FRー585Vile d o n■ List of Viledon air ﬁlter applications
Application

Spray-painting
booth

Drying oven

Types

Filters for painting booths almost completely remove large ・PA/350HL
visible particles (10µm or larger) that make up the suspended ・PA/305HL
dust particles in the air and are therefore eﬀective in reducing ・PHー400
paint defects.
Heat-resistant ﬁlters for drying ovens eﬃciently remove tar, soot,rust and other substances that are created inside a drying oven to ・AI ー100W
prevent surface contamination to products that undergo the drying ・AEー100 Two-ply
・AEー100
process. These ﬁlters are made of special synthetic ﬁbers thatdeliver excellent durability even in high-temperature environments.

General-purpose
regenerative

General-purpose regenerative ﬁlters are optimum for ﬁltering ・PS/600N
outdoor air or as a pre-ﬁlter to mid- to high-performance ﬁlters. ・PS/400N
They can be washed several times for easy regeneration.
・PS/300N
These ﬁlters are primarily used in panel format.
・PS/150N

General-purpose
disposable

General-purpose disposable ﬁlters are optimum for ﬁltering ・FRー585
outdoor air. FR-585 in particular delivers excellent running ・FSー6200
costs when used in automatic roll ﬁlter(V・MR). These ﬁlters ・FSー6500
have been treated with a adhesive to improve collection ・PE/205HL
・FRー580eﬃciency making it an eﬀective ﬁlter against sandy dust.

Specialequipment

Filters for special equipment deliver low pressure loss and・FSー1710
excellent collection eﬃciency for better dust holding capacity. ・FSー1705
This material can be cast with plastic or folded into a zig-zag ・FSー1705W
conﬁguration, and is optimally suited for maintaining a varietyof equipment for example when used as a medium for long-life
ﬁlters used in individual air-conditioning facilities.

Semi-conductorplant
3

Notable features

This type of Viledon ﬁlter has been given a low gas generation ・FRー580ーOGL
treatment, and is optimally suited for use as outdoor air ﬁltersfor cleanrooms in semi-conductor and LCD plants.

■ Features●Flexible in density control
The fabrics have a porous structure, whose pore sizes can becontrolled using diﬀerent combinations of ﬁber and binders to meeta variety of applications.

●Its "density gradient" is optimum for air ﬁlters.
With a graduated density that is greater on the downstream sidethan on the upstream, these ﬁlter media deliver minimal pressure
loss, good collection eﬃciency, and large holding capacity.
(Some products do not have a density gradient)"Density gradient" structure●Easy to regenerate.
Viledon air ﬁlters for general regeneration purposes can be regenerated using water
washing or spray cleaning.

●Peace of mind with excellent ﬂame retardancy
These products are categorized in Class 3 according to the Japan Air Cleaning Association's (JACA)
Flammability Test No. 11A-2003 for Air Puriﬁer Filter Media.
・FR-580 and FR-580-OGL are not ﬂame retardant.

●Versatile and suited for a variety of applications
These media are employed in a diverse range of applications ranging from everyday
uses in oﬃce buildings and music halls, to applications in state-of-the-art facilities suchas semiconductor factories.

■ List of Viledon air ﬁlter Speciﬁcation
Application

Types
PA/350HL

Material

Standard size Thickness Thermal Velocity Pressure drop（Pa） ASHRAE
averagestability
WxL（ｍｍ）（ｍ/ｓ） Initial Final arrestance
（℃）
（％）

18±3
19±3
PHー40018±3
AIー100W
500ｍm×500ｍm 20±3
Drying oven AE-100 Two-ply Aromatic polyamides 500ｍm×500ｍm 20±4
AEー1001.6ｍ×20ｍ 10±2
20±3
PS/600N
1.6ｍ×20ｍ 14±2
PS/400N
General-purpose
Polyester/modacrylic
10±2
regenerative PS/300N
1.6ｍ×30ｍ
8±2
PS/150N
Polyoleﬁn
FRー5851.73ｍ×20ｍ 18±3
Polyester/modacrylic
FSー6200
1.6ｍ×15ｍ 14±2
General-purpose
Polyester/modacrylic
1.6ｍ×20ｍ 13±2
disposable FSー6500
Polyoleﬁn
PE/205HL
1.6ｍ×20ｍ 18±3
Polyoleﬁn
FRー580※1.6ｍ×20ｍ 20±3
Polyamide/modacrylic
11±2
FSー1710SpecialPolyester/modacrylic
1.0ｍ×50ｍ
5.5±1.5
FSー1705
equipment
6.5±1.5
Polyester/modacrylic
FSー1705W

Spray painting PA/305HL
booth

Semi-conductor
FRー580ーOGL※plant

Polyoleﬁn

Polyoleﬁn

1.6ｍ×20ｍ

1.6ｍ×20ｍ

20±3

≦60
≦100

0.5

≦240
≦180
≦180

1.0

≦80

2.5

2.5
≦60

1.0
2.5

≦60

2.5

≦60

2.5

45
45
45
45
45
25
90
64
54
30
59
54
35
40
54
35
20
20
54

400

200

200

200

200
200

＞98
≧98
≧98
90
90
88
82
76
73
63
85
78
90
90
80
74
68
68
80

※FR-580 and FR-580-OGL are not ﬂame retardant.
※Filter thickness can be thinner according to storage condition.
Because inner part of roll type ﬁlters especially has a tendency to become thinner, thickness information on this catalogue is not guaranteed value.

4

PANEL FILTER

These ﬁlters are framed air ﬁlters that were designed to maximize the performance of Viledon ﬁlter media.
These ﬁlters are optimally suited for general-purpose treating of outdoor air, and as a pre-ﬁlter for mid- tohigh-performance ﬁlters.

■ VT series (aluminum frame, lightweight)

Lightweight and easy to handle. Model variations thatcan be joined together laterally are also available.

■ VA series (aluminum frame, detachable frame)

The inner frame can be easily removed from the outer
frame for easy replacement of the ﬁlter medium. The
frame is made of anti-corrosion aluminum, making it
lightweight and easy to handle.

■ VB series(aluminum frame, detachable frame/bolt-connected)

VT

This is an easy-to-assemble, bolt-connected type of ﬁlter.

■ VP series (built-in Viledon zig-zag format)

The ﬁlter surface is assembled in a zig-zag fashion to givethis air ﬁlter a three-fold increase in ﬁltering area.
This allows users to extend their replacement cycles forexcellent economy.

VP■ VK series (paper frame, disposable)

These ﬁlters are made by encapsulation-molding pleatedﬁlter media onto a frame made of recycled paper using a
special adhesive. A notable feature of this long-lastingand highly economical ﬁlter are the waste reduction
measures that have been taken.

VK

AUTOMATIC ROLL FILTER

Autmatic Roll ﬁlters are an automatic roll ﬁltration system that was developed through our extensive
experience in marketing Viledon ﬁlters over the years. A variety of sizes to suit customer requirements areavailable in a range of diﬀerent categories that respectively range from (1) coarse dust ﬁlters to mid- and higheﬃciency ﬁlters, (2) standard air volume to large air volume ﬁlters, and (3) generic ﬁlters with simple shape tohigh-performance ﬁlters.

【Automatic Roll Filter】■ V・M R series<Standard>

Equipped with Viledon, The V・MR is a system thatcollects dust on the surface of its ﬁlter media.
This is an automatic roll air ﬁlter with a drive
mechanism that automatically winds used media
and exposes new media.

■ V・H R series<Larger air volume>

The V・HR is an automatic roll air ﬁlter designed totreat large air volumes with Viledon media installed
in a zig-zag conﬁguration.

■ V・B R series<Automatic Roll air ﬁlter + Pocket ﬁlter>

The V・BR is a mid- to high-performance grade air
ﬁlter system that is a combination of an automaticroll ﬁlter and pocket ﬁlter.
With low pressure loss, high collection eﬃciency,
and long service life, this system delivers extremely
large dust holding capacity and can therefore beused for extended periods of time.

5Environment-friendly ﬁlter series

Middle and High Eﬃciency Filtraion

The environment-friendly ﬁlter series of mid- to high-performance ﬁlters is optimally suited for green
procurement purposes for a variety of businesses, as well as for improving general indoor air quality (IAQ)
in buildings.
This series of ﬁlters is equipped with a new type of ﬁlter media that were developed through Japan
Vilene's superior non-woven technologies.

Notable Features of the Environment-friendly ﬁlter series of Air Filters
Filter is made of self-developed non woven media that delivers low pressure loss, high eﬃciency,
and long service life.
Low pressure loss results in a reduction in power consumption of approximately 24%(Compared to previous Japan Vilene products).
Filter can be reused as a resource when recycled through our "used ﬁlter recycling system."
RPF implementation results in a roughly 30% reduction in CO2 emissions during recycling
compared to when coal is used.
The amounts of regulated chemical substances halogen※1, formaldehyde※2, and VOCs※3 usedhave been reduced.
Smaller volume and reduced weight thanks to thinner design and removable format.

Environment-friendly ﬁlter※1）Does not contain halogen series raw materials.
※2）Does not contain raw materials that generate formaldehyde.
※3）Reduced VOC (volatile organic compounds) content. (Compared to previous Japan Vilene products)

Rigid Filter

These ﬁlters are a mid- to high eﬃciency ﬁlter with a smaller volume and a【Element changeable】 replaceable medium. Its outer frame can be reused with only the element requiring
replacement to achieve a dramatic reduction in running costs.

■ V Z・D H series<Larger air volume>

Element
Model

VZ・DHー95Mー70F3
VZ・DHー95Mー35H3

95%

VZ・DHー95Mー35V1
VZ・DHー90Mー70F3
VZ・DHー90Mー35H3

90%

VZ・DHー90Mー35V1
VZ・DHー65Mー70F3
VZ・DHー65Mー35H3

65%

VZ・DHー65Mー35V1■ V Z・D T series<150mm depth>

70
（56
35
（28
35
（28
70
（56
35
（28
35
（28
70
（56
35
（28
35
（28

150
270×590×300
120）160130） 300 270×285×300
160
110×590×300
130）
130
270×590×300
100）140110） 300 270×285×300
140
110×590×300
110）
120
270×590×300
90）130100） 300 270×285×300
130
110×590×300
100）

Model

Model

Total
Dimensions（mm）Weight weight
W×H×D（kg） （kg）

3.0 VCー290Hー70F3 610×610×290 6.5

9.5

1.5 VCー290Hー35H3 610×305×290 5.0

6.5

1.0 VCー290Hー35V1 305×610×290 5.0

6.0

3.0 VCー290Hー70F3 610×610×290 6.5

9.5

1.5 VCー290Hー35H3 610×305×290 5.0

6.5

1.0 VCー290Hー35V1 305×610×290 5.0

6.0

3.0 VCー290Hー70F3 610×610×290 6.5

9.5

1.5 VCー290Hー35H3 610×305×290 5.0

6.5

1.0 VCー290Hー35V1 305×610×290 5.0

6.0

Element
JIS dust-spot
eﬃciency

Outer frame（standard）

Air ﬂow rate
（m3／min）

VZ・DTー95Mー56F5

Pressure drop（Pa）
InitialFinal

Weight
（kg）

Model

Total
Dimensions（mm）Weight weight
（kg）
（kg）
W×H×D

VCーDTー56F5 610×610×150 4.5

6.5

1.5 VCーDTー28H5 610×305×150 3.0

4.5

140

1.0 VCーDTー28V2 305×610×150 3.0

4.0

56

110

2.0

VCーDTー56F5 610×610×150 4.5

6.5

28

120

1.5 VCーDTー28H5 610×305×150 3.0

4.5

VZ・DTー90Mー28V2

28

120

1.0 VCーDTー28V2 305×610×150 3.0

4.0

VZ・DTー65Mー56F5

56

90

2.0

VCーDTー56F5 610×610×150 4.5

6.5

28

100

1.5 VCーDTー28H5 610×305×150 3.0

4.5

28

100

1.0 VCーDTー28V2 305×610×150 3.0

4.0

56

130

28

140

VZ・DTー95Mー28V2

28

VZ・DTー90Mー56F5

VZ・DTー95Mー28H5

VZ・DTー90Mー28H5

VZ・DTー65Mー28H5

95%

90%

65%

VZ・DTー65Mー28V2■ V Z・D series<Standard air volume>

Outer frame（standard）

JIS dust-spot Air ﬂow rate Pressure drop（Pa） Folded dimensions (mm) Weight
W×H×D
（kg）
eﬃciency （m3／min） Initial Final

2.0
300

300

300

Element
Model

Outer frame（standard）

JIS dust-spot Air ﬂow rate Pressure drop（Pa） Folded dimensions（mm） Weight
W×H×D
（kg）
eﬃciency （m3／min） Initial Final

VZ・Dー95Mー56F3

Model

Total
Dimensions（mm）Weight weight
（kg）
W×H×D
（kg）

270×580×290 3.0 VCー290ー56F3 610×610×290 7.0 10.0

56

130

28

140

300 270×275×290 1.5 VCー290ー28H3 610×305×290 5.0

6.5

VZ・Dー95Mー28V1

28

140

110×580×290 1.0 VCー290ー28V1 305×610×290 5.0

6.0

VZ・Dー90Mー56F3

56

110

270×580×290 3.0 VCー290ー56F3 610×610×290 7.0 10.0

VZ・Dー95Mー28H3

95%

28

120

300 270×275×290 1.5 VCー290ー28H3 610×305×290 5.0

6.5

VZ・Dー90Mー28V1

28

120

110×580×290 1.0 VCー290ー28V1 305×610×290 5.0

6.0

VZ・Dー65Mー56F3

56

90

270×580×290 3.0 VCー290ー56F3 610×610×290 7.0 10.0

28

100

300 270×275×290 1.5 VCー290ー28H3 610×305×290 5.0

6.5

28

100

110×580×290 1.0 VCー290ー28V1 305×610×290 5.0

6.0

VZ・Dー90Mー28H3

VZ・Dー65Mー28H3
VZ・Dー65Mー28V1

90%

65%

6

Environment-friendly ﬁlter

Rigid Filter【Box-shaped】

These ﬁlters are a mid- to high eﬃciency ﬁlter in a unit format. This series is
optimally suited for air-conditioning in buildings as well as for a variety ofindustrial applications.

■ V Z・H series <Larger air volume>Model

JIS dust-spot Air ﬂow rate Pressure drop（Pa）
eﬃciency（m3／min） Initial
Final

VZ・Hー95Mー70F
VZ・Hー95Mー35H

95%

VZ・Hー95Mー35V
VZ・Hー90Mー70F
VZ・Hー90Mー35H

90%

VZ・Hー90Mー35V
VZ・Hー65Mー70F
VZ・Hー65Mー35H

65%

VZ・Hー65Mー35V■ V Z・E series <Standard air volume>

Model

300

300

610×610×290

7.0

610×305×290

5.0

305×610×290

5.0

610×610×290

7.0

610×305×290

5.0

305×610×290

5.0

610×610×290

7.0

610×305×290

5.0

305×610×290

5.0

Dimensions（mm） Weight
（kg）
W×H×D
610×610×290 5.5

140

28

140

610×305×290

4.0

VZ・Eー95Mー28V

28

140

305×610×290

4.0

VZ・Eー90Mー56F

56

100

610×610×290

5.5

28

100

610×305×290

4.0

VZ・Eー90Mー28V

28

100

305×610×290

4.0

VZ・Eー65Mー56F

56

70

610×610×290

5.5

28

70

610×305×290

4.0

28

70

305×610×290

4.0

VZ・Eー65Mー28H
VZ・Eー65Mー28V

Model

95%

90%

65%

300

300

300

JIS dust-spot Air ﬂow rate Pressure drop（Pa）
eﬃciency （m3／min） Initial
Final

VZ・Tー95Mー56F

Dimensions（mm） Weight
（kg）
W×H×D

610×610×150

4.0

610×305×150

3.0

160

305×610×150

3.0

56

120

610×610×150

4.0

28

120

610×305×150

3.0

VZ・Tー90Mー28V

28

120

305×610×150

3.0

VZ・Tー65Mー56F

56

90

610×610×150

4.0

28

90

610×305×150

3.0

28

90

305×610×150

3.0

56

160

28

160

VZ・Tー95Mー28V28

VZ・Tー90Mー56F

VZ・Tー95Mー28H

VZ・Tー90Mー28H

VZ・Tー65Mー28H
VZ・Tー65Mー28V

Model

95%

90%

65%

300

300

300

JIS dust-spot Air ﬂow rate Pressure drop（Pa）
eﬃciency（m3／min） Initial
Final

VZー95Mー56F

Dimensions（mm） Weight
（kg）
W×H×D
610×610×290 7.0

56

120

28

120

610×305×290

5.0

VZー95Mー28V

28

120

305×610×290

5.0

VZー90Mー56F

56

100

610×610×290

7.0

28

100

610×305×290

5.0

VZー90Mー28V

28

100

305×610×290

5.0

VZー65Mー56F

56

70

610×610×290

7.0

28

70

610×305×290

5.0

28

70

305×610×290

5.0

VZー95Mー28H

VZー90Mー28H

VZー65Mー28H
VZー65Mー28V

7

300

56

VZ・Eー90Mー28H■ V Z series <Longer lite>

140
110）
140
110）
140
110）
120
90）
120
90）
120
90）
100
70）
100
70）
100
70）

JIS dust-spot Air ﬂow rate Pressure drop（Pa）（m3／min） Initialeﬃciency
Final

VZ・Eー95Mー56F
VZ・Eー95Mー28H■ V Z・T series <150mm depth>

70
（56
35
（28
35
（28
70
（56
35
（28
35
（28
70
（56
35
（28
35
（28

Dimensions（mm） Weight
（kg）
W×H×D

95%

90%

65%

300

300

300

Environment-friendly ﬁlter

These ﬁlters are a high-performance ﬁlter that was designed to prevent salt
Rigid Filter
damage and is eﬀective in preventing salt damage-related problems with
【Prevent sea salt particle】 air-conditioner ducts, digital oﬃce equipment, and production facilities.

■ V X・D series<Element changeable>

Element
Model

Outer frame（standard）

JIS dust-spot Air ﬂow rate Pressure drop（Pa） Folded dimensions (mm) Weight
W×H×D
（kg）
eﬃciency （m3／min） Initial Final

Model

Total
Dimensions（mm） Weight Weight
W×H×D（kg） （kg）

56

130

300 270×580×290 3.0 VCー290Sー56F3 610×610×290 7.0

10.0

28

140

300 270×275×290 1.5 VCー290Sー28H3 610×305×290 5.0

6.5

VX・Dー98Mー28V1

28

140

300 110×580×290 1.0 VCー290Sー28V1 305×610×290 5.0

6.0

VX・Dー95Mー56F3

56

120

300 270×580×290 3.0 VCー290Sー56F3 610×610×290 7.0

10.0

28

130

300 270×275×290 1.5 VCー290Sー28H3 610×305×290 5.0

6.5

28

130

300 110×580×290 1.0 VCー290Sー28V1 305×610×290 5.0

6.0

VX・Dー98Mー56F3
VX・Dー98Mー28H3

VX・Dー95Mー28H3

98%

95%

VX・Dー95Mー28V1■ V X series <Standard>
Model

JIS dust-spot Air ﬂow rate Pressure drop（Pa）
eﬃciency（m3／min） Initial
Final

VXー98Mー56F

Dimensions
（mm）
W×H×D

Weight（kg）

610×610×290

7.0

610×305×290

5.0

56

120

28

120

VXー98Mー28V

28

120

305×610×290

5.0

VXー95Mー56F

56

110

610×610×290

7.0

28

110

610×305×290

5.0

28

110

305×610×290

5.0

VXー98Mー28H

VXー95Mー28H

98%

95%

VXー95Mー28V

300

300

Environment-friendly ﬁlter
Pleated Filter

With a depth measuring only 65mm, These ﬁlters are a series of thin andlightweight mid- to high-performance ﬁlters that deliver low pressure loss with a
conﬁguration where the media is folded into ﬁne pleats.

■ V M・D series<Element changeable 65mm>

Element
Model

VM・Dー90Mー56F
VM・Dー90Mー23H

56

90%

23

VM・Dー90Mー23V

23

VM・Dー65Mー56F

56

VM・Dー65Mー23H
VM・Dー65Mー23V

Outer frame（standard）

65%

23

90

70

23

Total

Model

Dimensions（mm） Weight Weight
W×H×D（kg） （kg）

604×608×53 1.5

VCー65ー56F

610×610×65 1.5

3.0

300 604×304×53 1.0

VCー65ー23H

610×305×65 1.0

2.0

299×608×53 1.0

VCー65ー23V

305×610×65 1.0

2.0

JIS dust-spot Air ﬂow rate Pressure drop（Pa） Dimensions (mm) Weight
eﬃciency（m3／min） Initial Final
W×H×D
（kg）

604×608×53 1.5

VCー65ー56F

610×610×65 1.5

3.0

300 604×304×53 1.0

VCー65ー23H

610×305×65 1.0

2.0

299×608×53 1.0

VCー65ー23V

305×610×65 1.0

2.0※The VM・D-90M series uses media that has been given an electriﬁcation treatment.

■ V M series <Standard 65mm>
Model

JIS dust-spot Air ﬂow rate Pressure drop（Pa）
eﬃciency （m3／min） Initial Final

VMー90Mー56F

56

VMー90Mー23H

90%

Dimensions（mm） Weight
W×H×D
（kg）

610×610×65

3.0

610×305×65

2.0

VMー90Mー23V

23

305×610×65

2.0

VMー65Mー56F

56

610×610×65

3.0

610×305×65

2.0

305×610×65

2.0

VMー65Mー23H
VMー65Mー23V

65%

23

23
23

90

70

300

300

※The VM-90M series uses media that has been given a electriﬁcation treatment.

8

Environment-friendly ﬁlter
Pocket Filter

With superb collection eﬃciency and low pressure drop, the VG series delivers
excellent dust holding capacity. As such, this is a streamer type ﬁlter that can be used
for longer periods of time compared to unit type ﬁlters.

Notable Features of the Environment-friendly ﬁlter series of Pocket Air Filter

Based on innovative self-developed nonwoven fabric.
Low pressure loss results in a roughly 24% reduction in power consumption(Compared to previous Japan Vilene products).［VG-95M］
Roughly 150% longer service life (Compared to previous Japan Vilene products).

［VG-95M,VG-90M］

Smaller CO 2 emissions in terms of LCA (Life Cycle Assessment).

■ V G series

JIS dust-spot Air ﬂow rate Pressure drop（Pa）
eﬃciency （m3／min） Initial
Final

Model

VGー95Mー56F
VGー95Mー28H

95%

56

130

28

130

300

Dimensions
（mm）
W×H×D

Pocket Weightmumber （kg）

595×595×860

6

3.0

595×305×860

6

2.0

3

2.0

VGー95Mー28V

28

130

305×595×860

VGー90Mー56F

56

110

595×595×860

6

3.0

28

110

595×305×860

62.0

VGー90Mー28V

28

110

305×595×860

32.0

VGー70Mー56F

56

90

595×595×860

63.0

VGー70Mー28H

28

90

595×305×860

6

2.0

28

90

305×595×860

32.0

VGー90Mー28H

90%

70%

VGー70Mー28V

300

300

Filters related to Pocket Filter■ V G ー4 0 seriesThis is a lightweight ﬁlter witha plastic frame that provides
excellent shape retention, andis optimally suited for use as a
pre-ﬁlter for high-performanceﬁlters or an intermediate ﬁlter
within a ceiling ﬁlter system inspray-painting booths.

9

Model

JIS dust-spot Air ﬂow rate Pressure drop（Pa） Folded dimensions（mm） Pocket Weight
WxHxD
mumber （kg）
eﬃciency （m3／min） Initial Final

VGー40ー70F

70

70

595×595×350

41.0

VGー40ー35H

35

70

595×305×350

40.6

VGー40ー35V

3570

305×595×350

2

0.6

56

70

595×595×280

40.9

VGー40ー28H

28

70

595×305×280

40.5

VGー40ー28V28

70

305×595×280

2

0.5

VGー40ー56F

40%

300

RIGID FILTER CASING SERIESWith the enactment of the Law for Maintenance of Sanitation in Buildings, ﬁlter performance levels have evolved asenvironmental standards for designated buildings, and cleanness level requirements in industrial spaces havebecome more stringent. Coupled with demand for greater economic performance, space-saving air-conditioning
equipment that provide good eﬃciency in terms of both function and cost have become indispensable.
Specially designed for coarse dust ﬁlters, mid- to high eﬃciency ﬁlters, and HEPA ﬁlters, the ﬁlter casing series ofcasings meet these new demands.

Filter casing (For Panel ﬁlter VT)■ V T・C A series

The VT・CA is used together with Japan Vilene's Panel ﬁlter
VT as a primary treatment ﬁlter for outdoor air.

Filter casing (For Pleated ﬁlter VM)■ V M・C A series

The main ﬁlter of the VM・CA consists of the environmentally-friendly ﬁlter.Users can choose from one that is ﬁtted with a
pre-ﬁlter, or one without.

Filter cam casing■ V・C M series

The V・CM casing consists of a pre-ﬁlter and main ﬁlter
conﬁguration. The main ﬁlter is ﬁxed in place by way of acam. Its main ﬁlter consists of the environmentally-friendly
ﬁlter.

Automatic roll air ﬁlter + ﬁlter cam casing■ V・C M・R series

A design that combines pre-ﬁlter main ﬁlter, makes the
V・CM・R a labor-saving ﬁlter casing.
Its main ﬁlter consists of the environmentally-friendly
ﬁlter.

Super-high-performance ﬁlter casing■ V・C M・H series <HEPA ﬁlter>

The V・CM・H is a super-high-eﬃclency ﬁlter casing thatwas developed specially for HEPA ﬁlters.
It comes with a special, high-precision tightening
mechanism for installing HEPA ﬁlters.

【Filter installation frame】

VC Studs <Midium Eﬃciency ﬁlter> series※VC-100E●

4080W

VC Studs<HEPA ﬁlters> series

100

630 3ヶ=1890

100

Depth: 900 or more

100

630 2ヶ=1260

100

630 3ヶ=1890

For reinforcement, use a bent member measuring

2820Ｈ

Installation frames
・VCー100E (For VZ・H,VZ・E,and VZ only)
・VCー100T (For VZ・T only)
・VCー100ES (For VX only)
・VCー100VM (For VM only)(For VG only)
・VCーVG
Outer frames
・VCー290H (For VZ・DH only)(For VZ・D only)
・VCー290(For VZ・DT only)・VCーDT
・VCー290S (For VX・D only)(For VM・D only)
・VCー65100

100 630 2ヶ=1260●<Example of casing frame construction> (4 rows x 6 columns)

400W

100 100 3.2.

・The drawing is an example where VC-100E-56F is used.

Installation frame VC-150H（For HEPA ﬁlters only）

10

GAS REMOVAL FILTER
These ﬁlters are a series of ﬁlters that were designed to remove※ gases withfoul odors or harmful gases using active carbon and chemical adsorbent.
※This in no way implies that these filters guarantee personal safety.
※Effectiveness varies depending on the type of gas. Please call Japan Vilene for details.

■ V Z・G series <Foul odor gas and harmful gas ﬁlter with dust removal function>
These ﬁlters are a combination of a layer of adsorbent for removing foul odors and harmful gases, and a layer for removing dust particles.

High-dust-removal-eﬃciency ﬁlter(Dust - spot grade)

Model

Dimensions (mm)
W×H×D

JIS dust-spot eﬃciency

Adsorption capacity※1（g/ﬁlter）

Air ﬂow rate
（m3／min）

VZ・Gー90Aー56F
VZ・Gー90Aー28H
VZ・Gー90Aー28V

610×610×290
610×305×290
305×610×290

90%

96
48
48

VZ・Gー65Aー56F
VZ・Gー65Aー28H
VZ・Gー65Aー28V

610×610×290
610×305×290
305×610×290

VZ・Gー90Bー56F
VZ・Gー90Bー28H
VZ・Gー90Bー28V

Pressure drop（Pa）
InitialFinal

Weight
（kg）

56
28
28

140

65%

96
48
48

56
28
28

300

10.5
6.0
6.0

90

10.5
6.0
6.0

610×610×290
610×305×290
305×610×290

90%

41
21
21

56
28
28

140

VZ・Gー65Bー56F
VZ・Gー65Bー28H
VZ・Gー65Bー28V

610×610×290
610×305×290
305×610×290

65%

41
21
21

56
28
28

300

10.5
6.0
6.0

90

10.5
6.0
6.0

VZ・Gー90Cー56F
VZ・Gー90Cー28H
VZ・Gー90Cー28V

610×610×290
610×305×290
305×610×290

90%

551
276
276

56
28
28

140

VZ・Gー65Cー56F
VZ・Gー65Cー28H
VZ・Gー65Cー28V

610×610×290
610×305×290
305×610×290

65%

551
276
276

56
28
28

300

10.5
6.0
6.0

90

Acidicgas

VZ・Gー20Aー56F
VZ・Gー20Aー28H
VZ・Gー20Aー28V

610×610×290
610×305×290
305×610×290

90%

96
48
48

56
28
28

70

300

10.0
5.5
5.5

Basic
gas

VZ・Gー20Bー56F
VZ・Gー20Bー28H
VZ・Gー20Bー28V

41
21
21

56
28
28

70

300

10.0
5.5
5.5

Organic
solventgas

VZ・Gー20Cー56F
VZ・Gー20Cー28H
VZ・Gー20Cー28V

610×610×290
610×305×290
305×610×290
610×610×290
610×305×290
305×610×290

551
276
276

56
28
28

70

300

10.0
5.5
5.5

Types

Acidic
gas

Basic
gas

Organic
solventgas

Low-pressure-loss type
(Arrestance grade)

※2

※2

90%

※2

90%

10.5
6.0
6.0

● ※1）Adsorption capacity refers to the volume of gas a single test filter was able to adsorb up to the point where gas permeability reached 95% (breakthrough) as a result of having
fed with acidic gas (sulfur dioxide at 30 ppm), basic gas (ammonia at 30 ppm), and organic solvent gas (toluene at 80 ppm). (Test conducted in accordance with DIN71460 Part 2)● ※2）Collection efficiency indicates collection efficiency (%) as stipulated in the JIS arrestance.
● Please consult with Japan Vilene for specific types and concentrations of different organic solvent gases.

■ V T・G series <Foul odor gas and harmful gas ﬁlter>
These are space-saving, low-pressure-loss ﬁlters.
Types

Model

Low-pressure-loss, thin ﬁlter(Arresta grade)

VT・Gー6161ー65A

Acidic VT・Gー6161ー50A
gas
VT・Gー6161ー35A※1
Dimensions（mm）
Adsorption capacity Air ﬂow rate Pressure drop（Pa） Weight
JIS arrestams eﬃciency （g/ﬁlter） （m3／min）
W×H×D
Initial Final （kg）
610×610×65
5
45
90%
27
50
300
610×610×50
4
34
610×610×35
3
23

VT・Gー6161ー65B
VT・Gー6161ー50B
VT・Gー6161ー35B

610×610×65
610×610×50
610×610×35

Organic VT・Gー6161ー65C
solvent VT・Gー6161ー50C
VT・Gー6161ー35C
gas

610×610×65

Basic
gas

arrestams

610×610×35

90%

23
17
11

27

50

300

5
4
3

90%

224
168
112

27

50

300

5
4
3

● ※1）Adsorption capacity refers to the volume of gas a single test filter was able to adsorb up to the point where gas permeability reached 95% (breakthrough) as a result of having
fed with acidic gas (sulfur dioxide at 30 ppm), basic gas (ammonia at 30 ppm), and organic solvent gas (toluene at 80 ppm). (Test conducted in accordance with DIN71460 Part 2)● Available in custom sizes.
● Specific dimensions apply if used as a replacement to the model VC・L palette filter.
● Please consult with Japan Vilene for specific types and concentrations of different organic solvent gases.

■ V C・L series <Foul odor gas and harmful gas ﬁlter, adsorbent-ﬁlled>
These are adsorbent-ﬁlled ﬁlters that eﬃciently remove foul odors and harmful gases through optimum selections of chemical adsorbent
and active carbon. At the end of the ﬁlter life, the adsorbent in the palette can be replaced without having to replace the casing.
Model

※3

Weight of adsorbent（kg/ﬁlter） Weight of casing and
Palette（L/ﬁlter） E3☆、A2☆ FF☆ 02☆、KK☆ palette frame（kg/ﬁlter） Quantity Dimensions (mm) W×H×D

Air ﬂow rate Initial pressure drop Filling capacity

Dimensions (mm)
W×H×D

（m3／min）

（Pa）

VC・Lー

ー56F

610×610×460

56

170

57

39

47

30

43

8

600×400×35

VC・Lー

ー28H

610×305×460

28

170

28.5

19

23

15

25

4

600×400×35

VC・Lー

ー28V

305×610×460

28

170

28

19

24

15

28

8

295×400×35

VC・Lー

ー30F

610×610×290

30

100

34

22

27

17

31

8

600×230×35

VC・Lー

ー14H

610×305×290

14

100

17

11

13

8

19

4

600×230×35

VC・Lー

ー14V

305×610×290

14

100

16.5

11

13

8

21

8

295×230×35● ※3）Pressure loss indicates the initial value at air flow rate when it is filled with KK.
● The "☆" indicates the symbol of the adsorbent's target gas. Please refer to the VILO FRESH catalog for details.
● Versions with pre-filters are also available.

11

HEPA / ULPA FILTER

Unit ﬁlters (High Eﬃciency Particlate Air Filter)

As the electronic and precision instrument industries continues togrow, the demand for extremely clean air has also been growing fromthe perspective of productivity and quality management. HEPA andULPA ﬁlters are essential in creating air that meets these cleanness
standards. Based on our many years of experience in the
air-conditioning industry, Japan Vilene has been developing andmarketing HEPA and ULPA ﬁlters for many years that meet thedemands of these markets.

HE PA F IL T E R■ VN series <Standard ﬁlter>

These ﬁlters were designed to be used as mainﬁlters in cleanrooms and cleanroom equipment.

Types
HEPA
standard VN

Air ﬂow rate Initial pressure drop ※2
Collection eﬃciency （m／min）
3
（Pa）
※1
At least 99.97%
245
VNー100ー＊＊＊ of 0.3µm particles. 3.7〜64.5
Model■ VH series <Large air volume ﬁlter>

Air ﬂow rate Initial pressure drop ※2
Collection eﬃciency （m／min）
3
（Pa）
※1
HEPA
At least 99.97%
7.8〜55.0245large air volume type VH VHー100ー＊＊＊ of 0.3µm particles.

■ VY series <Separator-less ﬁlter>

Air ﬂow rate Initial pressure drop ※2
Collection eﬃciency （m／min）
3
（Pa）
※1
152Pa
At least 99.97%
Separator-less HEPA
at 0.5m/s
super thin type VY VYー100ー＊＊＊ of 0.3µm particles. 6.5〜20.7

These ﬁlters have a smaller pressure drop thanthat of VN (standard) ﬁlters. At the same pressure
drop, these ﬁlters are capable of treating between
roughly 1.3 to 2 times the rated air volume.
These were designed to be used as main ﬁltersin cleanrooms and cleanroom equipment whichmust treat large volumes of air.

These are super-thin ﬁlters with a thicknessof only 45mm. They are designed for energy
conservation, can be ﬁtted with noise reduction
measures, and are optimally suited for a broad
range of instruments.

■ VQ series<Low-pressure-drop, separator-less ﬁlter>

These are thin ﬁlters with a thickness of only
66mm, and are optimally suited for cleanrooms
and various instruments that require low-pressureloss air treatment.

Types

Types

Model

Model

Air ﬂow rate Initial pressure drop ※2
Collection eﬃciency （m／min）
3
（Pa）
※1
167Pa
At least 99.97%
Separator-less HEPA
3.7〜64.5 at 0.84m/s
low-pressure-loss type VQ VQー100ー＊＊＊ of 0.3µm particles.
Types

Model

Types

Model

Semi-HEPA,
standard VN

VNー95ー＊＊＊Air ﬂow rate Initial pressure drop ※2
Collection eﬃciency （m／min）
3（Pa）
88Pa（depth: 150）
At least 95%
3.7〜64.5
of 0.3µm particles.
118Pa（depth: 290）

Types

Model

Air ﬂow rate Initial pressure drop ※2
Collection eﬃciency （m／min）
3（Pa）■ V N ー 9 5 series<95% eﬃciency, standard ﬁlter>

This is a series of semi-HEPA ﬁlters that are
optimum for cleanroom equipment and the likeincluding cleanroom changing rooms and passthrough chambers.

※1■ V H ー 9 5 series<95% eﬃciency, large air volume ﬁlter>

This is a series of semi-HEPA ﬁlters with a
rated air volume of between roughly 1.3 to
2 times that of VN-95 at the same pressure loss.

ULPA F IL T E R■ V U series<99.9995% eﬃciency, standard ﬁlter>

Semi-HEPA,
large air volume
type VH

Types
ULPA
Standard VU※1

VHー95ー＊＊＊At least 95%
of 0.3µm particles.

128Pa（depth: 75）
147Pa（depth: 150）
7.8〜55.0
167Pa（depth: 290）

ﬁlters〔Super large air volume
150/290〕

Air ﬂow rate
Collection eﬃciency （m／min）
3※1
At least 99.9995%
VUー100ー＊＊＊ of 0.15µm particles. 3.7〜64.5
Model

※2
Initial pressure drop

（Pa）

245
This series of ﬁlters are optimally suited as mainﬁlters used in spaces that require exceptionallyhigh levels of cleanness such as in the semiconductor ● ※1）The "＊＊＊" indicate the air flow rate and material. Please refer to the HEPA/ULPA catalog for details.
● ※2）Initial pressure drop values are indicated for air flow rate operation. Initial pressure drop air speed
industry, nuclear facilities and medical equipment.
varies depending on filter thickness. Please refer to the HEPA/ULPA catalog for details.

【Filter installation frame】VC Stud <HEPA ﬁlter> series■ VCー150H
VC-150H is an installation frame that was designed speciﬁcally for HEPA ﬁlters,
and allows users to easily assemble the ﬁlter without error.

12Special Applications
Anti-Viral Infection Filter■ VZ , V type

The VZ, V type ﬁlters mitigate the infectiousness of ﬂu
viruses that they collect. They help reduce the risk ofinfections in airports, train stations, hospitals, schools,
oﬃces and other large buildings and facilities where large
numbers of people gather.
※This filter will not completely eliminate the risk of disease or infection.

Anti-Pollen Air Shower■ V・AS-CB typeAnti-pollen Air shower uses jets of clean air to remove※
approximately 90% of plant pollen that can be attached
to our clothing.
With a slim and reﬁned design, Anti-pollen Air shower is
optimally suited for use in condominiums, hotels, andoﬃce buildings.
※ According to our test result.

Asbestos removal work
Japan Vilene also supplies an easy-to-install Air
shower, and Negative pressure dust remover, bothof which are essential in asbestos removal work.

■ Easy-to-Install Air shower

The easy-to-install Air shower
consists of a ﬁlter unit and blower
unit conﬁgured into a two-tiered
construction, and can therefore be
installed very easily at construction
sites.
※V・AS-0010S■ Negative pressure dust remover

Negative pressure dust remover isa unit that maintains negative
pressure on the inside of work
areas within demolition sites thathave been cordoned oﬀ to preventthe spreading of contaminationfrom designated dust particle suchas asbestos. The air is treated bya pre-ﬁlter, secondaryﬁlter(mid-performance), andmain ﬁlter (HEPA), after which
it is expelled outdoors.

※V・DC-65A● This is a general catalog for air-conditioning products marketed by Japan Vilene.
Please refer to individual product catalogs for more speciﬁc product information.
● If you do not have a product catalog, you can either download one from our web
site, or request one of our agents to have one mailed to you.

13

14

Head Office
5-6-4, Tsukiji, Chuo-ku, Tokyo 104-8423, JAPANTEL. +81-3-4546-1166 FAX. +81-3-4546-1162

15

2018.12 CP 0000