ENTRELECTERMINAL BLOCKS
Master catalog

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MASTER CATALOGENTRELEC Terminal Blocks
Master catalog

SNK SERIES TERMINAL BLOCKS

DEDICATED APPLICATIONS TERMINAL BLOCKSRGW RING LUG TERMINAL BLOCKSDBL POWER DISTRIBUTION BLOCKSESSAILEC® TEST BLOCKSRAILWAY APPLICATIONS TERMINAL BLOCKS

1-1773980-7_Couv1-summary_TE

MARKING SOLUTIONSEASY RAIL DESIGNER 3D

1-1773980-7_EN - Edition February 2020

PAGE 3

SNK SERIESTERMINAL BLOCKS
PI-Spring, screw clamp andpluggable technologies
ENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSExplanatory page

Here is the first SNK Series Terminal Blocks interactive catalog which contains
numerous new functionalities:dditional information, about the product pages:Ain the table, click on the product order code to obtain
the data sheet, the agreement and all technicalinformation regarding that reference.
dedicated page to the SNK challenge videos and theA
SNK videotab system on the side of the Flipbook helps youA
navigate easily inside the catalog

Interactive summaries. One click on an entry leads you
to the desired page.

Receive one link only in your email to open the Flipbook;once opened, you can download the PDF, only if you needto. No overload in your email box nor on your hard drive.

ZK2.5 PI-Spring terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

1

Description
Combine high performance with compact dimensions:– 1000 V AC / DC IEC 600 V UL,– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

1SNK162052V0014

Ordering details
Description
Feed-throughColor
2 connections

Grey
Blue
OrangeYellow
Green
Red
White
Black

ZK2.5

Type

Part Number

Pkg
qty

(1 pce) g

ZK2.5
ZK2.5-BL
ZK2.5-OR
ZK2.5-YL
ZK2.5-GN
ZK2.5-RD
ZK2.5-WH
ZK2.5-BK

1SNK705010R0000
1SNK705020R0000
1SNK705030R0000
1SNK705060R0000
1SNK705061R0000
1SNK705062R0000
1SNK705065R0000
1SNK705066R0000

50
50
50
50
50
50
50
50

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

UL - CSARail

Main technical data

41.7 1.64"

49.2 1.94"
24.6 0.97"

2

Mounting instructions

Connecting capacityIEC

50.9 2"

5.2 mm 0.205 in spacing

Weight1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 in

Click on the productpart number to obtain
detailed information andagreements.

Flat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Shield connectors
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey

White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
20
1960
22
20
10

5.30
1.80
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
4.10
0.23
9.00
10.00
0.20

Description
GroundColor
Profile aligned with ZK2.5

Green-yellow

TypePart Number

Pkg
qty

(1 pce) g

ZK2.5-PE

1SNK705150R0000

20

10.00

WeightTechnical data valid for copper conductors only.

PAGE 21

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160094S0201

Ground PI-Spring terminal blocks

1SNK162023S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Videos

SNK challenges
Discover how our SNK terminal blocks are able to overcome any kind of challenge!
What is the link between a terminal block, a washing machine, an egg and a child's play?
Find it out quickly by watching our 6 episodes bellow.
Get tips and experience moments of suspense and fun!

Episode 1
Built for extreme conditions?

Episode 4
So efficient marking?

Episode 2
So fast to connect?

Episode 5
Common accessories for alltechnologies?

Episode 3
Available everywhere on time foreveryone?

Episode 6
Mounting is a child's play?

SNK video

1SNK160094S0201

SNK Series - The innovative range.

Summary_1

The innovative SNK series is available in
PI‑Spring (Push-In and Spring), screw clamp andpluggable technologies with common accessories.
Qualiﬁed for worldwide applications and severe
environments such as hazardous locations, railways,
marine and solar.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal blocks

PI-Spring, screw clamp and pluggable technologies

2

1

PI-Spring terminal blocks

13

2

Screw clamp terminal blocks

71

3

Pluggable terminal blocks

161

4

Accessories

195

5Marking solutions

237

6

Index		

270

7

Summary_1

Ranges and technologies presentation

1-1773957-4_EN - Edition January 2020

PAGE 1

ENTRELEC Terminal blocks

TE Connectivity proposes one of the largest Din Rail Terminal block offering on themarket with various technologies: screw, PI-Spring, spring, IDC, pluggable, stud, etc.
found in over 8000 products & solutions.

1

Scope

SNK
terminal blocks

Dedicated applications
terminal blocks

Terminal blocks forrailway applications

Qualified for worldwide applications andsevere environments (such as hazardous
locations, railways, marine and solar
applications..).
From 0.2 to 300 mm².

Specific terminal blocks and technologies
for dedicated applications and markets.

The largest offering on
the market for rollingstock and infrastructures.

Product
SNK PI-Springfamilies & technology
functions 2.5 to 16 mm²
12 to 4 AWG

Feed-throughMulti-deck
GroundDisconnect
for fuses
Component holder

ADO System® (IDC)
0.22 to 4 mm²
24 to 12 AWG

ADO-ADO or ADO-screw clamp SNK PI-Spring technology
Feed-through / Multi-deck /2.5 to 16 mm²Ground / Disconnect /12 to 4 AWG
for fuses / Component holder

Safety (spring loaded)
0.22 to 10 mm²
24 to 6 AWG

Feed-throughDisconnect
Test & measurement

SNK pluggablescrew & PI-Spring technologies
2.5 to 4 mm²
12 to 10 AWG

SNK screw clamp
technology
4 to 240 mm²
12 to 500 Kcmil

Feed-throughMulti-deck
GroundDisconnect
for fuses
Test & measurement
Marshalling
Component holderStud
25 to 300 mm²
4 AWG to 1000 Kcmil

One stud
2 studs
One stud - One screw clamp

ADO System® (IDC)
1.5 to 4 mm²
16 to 12 AWG

Ring lug
6 to 16 mm²
8 to 6 AWG

Feed-throughTest & measurementStud
4 to 185 mm²

SNK pluggablescrew & PI-Spring
technologies
2.5 to 4 mm²
12 to 10 AWG

Feed-throughMulti-deck
GroundMiniblocks
1.5 to 6 mm²
18 to 8 AWG

Screw clamp
SpringADO System ® (IDC)

Quick-connect
2.5 to 6 mm²

Other types
Test & measurement: with sliding link, blade, plug
Pluggable: feed-through, double deck, disconnect
Sensors/actuators: screw, spring, ADO system (IDC)
Installation: screw, spring
Protection: ground + neutral
Component holders: screw, spring, ADO system (IDC)

www.te.com

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSDBL power
distribution blocks

ESSAILEC®
test blocks

Interfast PLC
pre-wiring system

Marking
solutions

The preferred choice for primary
power distribution and solar
applications.

Test blocks for safe and easy
testing on secondary circuitsof current and voltage
transformers and sensors.

PLC pre-wiring system for fast,
flexible, reliable connection of PLC’sin process automation applications.

Markers & marking systems for
all identification requirements inelectrical panels.

From 80 A up to 550 A (IEC)

Current and voltage
sockets & plugs

Interfast PCB:
Compact & standard modules

Terminal block identification andgroup markers

Simultaneous testing of
1 to 4 independent circuitson the same socket

Interfast MS:
Modular system based onterminal block technology

Wire and cable identification

Terminal blocks types:
2 to 10 poles, up to 20 outputs

Component and equipment
identification

Several testing principle such
Functions:as “make before break” for safe – – 1 to 4 wire connections (sensors) Panel identification
current transformer testing– – Disconnect
Pre-printed markers for terminal– – Fuse
blocksPanel and switchboard
mounting : base, flush, rack,– – Signal indication
TH35 rail– – Relays
Multicircuits sockets & plugs– – Optocouplers– – Solenoid valve control– – Galvanic isolation (2.5 kV).

1SNC160261S0201

Modular blocks: single pole, three& four poles, up to 12 outputs

1

PAGE 3

1SNK160093S0201 - Rev. A

1

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal blocks
PI-Spring, screw clamp and pluggable technologies

1

Speed up your projects
Smart connections, higher productivity
Up to 90% mounting time reduction with our PI-Spring, screw
clamp and pluggable technologies.
Simplified selection and design
Intuitive codification, simplified catalogs, large technicaldata base.
Better project identification
20% larger marking area.
Pre-mark by hand or label before final marker installation.

Easy to install
Secured installation
Asymmetrical design avoid mounting and wiring errors.
Zero-retightening with our technologies.
Faster accessories mounting
Benefit from screwless ground connection, jumpers, end stops.
Smart design facilitating assembly process
Mounting, wiring, testing… made easy.

Optimized logistics
50% less accessories needed
End sections, circuit separators fit several blocks.
Common accessories
PI-Spring, screw and pluggable ranges share the same
accessories.
Simplified inventory management
Significant reduction of part numbers to manage.

1SNK160093S0201 - Rev. A

The innovative range available
in PI-Spring (Push-In and Spring),screw clamp and pluggable
technologies with common
accessories.
Qualified for worldwide applications
and severe environments suchas hazardous locations, railways,
marine and solar applications...

PAGE 5

PI-Spring technology
Two technologies in one connection
The patented design of TE Connectivity’s PI-Spring can beused as a Push-in or traditional spring connection: Push-inand spring. The Push-in mode allows a direct one-step insertion of solid and flexible stranded wires with a ferrule, 50%
faster than standard screw clamp technology.

Using the spring mode, very little effort is required to open
the spring clamp with a screwdriver and insert the wire, which
does not need a ferrule. The screwdriver locks in the terminal
block after insertion, freeing up hands to manipulate wires or
circuit drawings.

1

FeaturesAll certification testing performed
with non prepared wires, ensuring
perfect connections withor without ferrules

Connection elasticity and design
strictly controlled to ensure an easyand safe insertion of both conductor
and screwdriver

The PI-Spring technology has successfully
passed aging tests (30 days temperature rise
test and 14 days heat cycling test)
guaranteeing the perfect long-term contact
quality of our screwless technology

Flat surface of the PI-Spring
makes wire and screwdriverinsertion smoother and easier

Excellent pulling strength
exceeding IEC standard
requirements
Dimensions, coating and shapeof the linking bar designed to
get the lowest and most stableelectrical contact value

Stainless steel PI-Spring forhigh corrosion resistance
up to 1,000 hours
salt mist resistance

Very good electrical contact
even in applications where
vibration and shock are an
issue, such as railway

From 0.2 mm² up to 16 mm²
1SNK162052S0201 - Rev. A

From 26 AWG up to 4 AWG

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSScrew clamp technology
The heavy duty connection
Unique design, flies over time thanks to its reliability
and safety
The TE Connectivity screw clamp technology is designed to
avoids accidental releases due to vibrations, shocks or evenabusive cable draw.

High density capacity
The screw clamp technology can fit up to two conductors per
clamp which offers extended possibilities in electrical cabinets.

1

Features

The clamp is punched, which
increases the number of screw
threads by 30% meaning ahigh torque resistance

The TE Connectivity exclusiveanti-release system creates acontrolled locking-screw effectthanks to the 2 overlappingtabs that maintain the clamp
parts. The screw is locked in
total safety. The retightening
campaigns are not needed
anymore!

Screw

Screw clamp
Conductive
linking bar
The screw tightens the
conductive bar to the cable.
There is no torsion effectapplied to the cable

Hardened steel makes theconnection very reliable

Stripped wire

Flap avoiding the insertionof cable underneath the clamp

From 0.2 mm² up to 240 mm²
1SNK161087S0201 - Rev. A

From 24 AWG up to 500 Kcmil

PAGE 7

Pluggable technology

The pluggable technology allows "plug and play" connection.
It enables productivity savings, wiring optimization thanks toserialized pre-wired plugs harnesses, as well as secured final
commissioning.

1

Features

The TE Connectivity plug is the mostcompact on the market thanks to thepunched U-shaped linking bar allowing
direct conductor contact.
TE Connectivity Patented design!

The chamfer shape guarantees auto-centeringand mechanical integrity of the plug wheninserted into the pluggable terminal block

The lyres are made of copper alloy inorder to offer maximized mechanicalelasticity resistance(superior to 50 matings/unmatings)

The TE Connectivity pluggable terminal
blocks have successfully performed
the marine environmental tests andmeet the most severe rolling stock
requirements in 3 axis vibrations
and shock resistance (for PI-Spring
pluggable terminal blocks versions)

From 0.2 mm² up to 4 mm²

1SNK164011S0201

From 26 AWG up to 10 AWG

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPB

1PAGE 9

SNK series, terminal blocks
Applications

Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…
Industry and Commercial

Solar

SNK series, terminal blocks can be used worldwide in all types of industrial and commercial
applications. All our products have CB, UL and CSA third party certificates delivered byindependent laboratories. SNK series products are developed and qualified in accordancewith the following international standards:
IEC 60947-1, IEC 60947-7-1, IEC 60947-7-2, IEC 60947-7-3, UL 1059, CSA C22.2 n°158-10.

Thanks to their high voltage rating(up to 1500 VDC per IEC 60947-7-1 and1000 VDC per UL 1059), SNK terminal
blocks are ideally suited for use in solar
equipment.

1

RoHS

SNK terminal blocks are well adapted toharsh environment conditions such aswaste and water applications.
They have successfully passed the salt mist
test in accordance with IEC 60068‑2-11(PI-Spring withstand up to >1000 h).
SNK terminal blocks are also compliant
with flowing mixed gas corrosion test per
IEC 60068-2-60 (test duration: 21 days).

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160082S0201 - Rev. A

Waste and Water

Railways

Hazardous locations

Marine1

SNK series is certified IEC Ex in accordancewith IEC 60079-0 and IEC 60079‑7(increased safety "Exe") world international
standards for products used in explosive
atmospheres.
In order to serve specific local market
requirements, some SNK products haveadditional local certifications such as: ATEX,UL hazardous Locations…
SNK products have successfully passed
toughest tests like the thermal endurance
test: 2 weeks in hot environment at 95 °C(+90% RH) followed by 2 weeks at 125 °C
and one day cold environment test (-65 °C).
This proves the high mechanical performancesof the SNK products.

hazloc

SNK products have proven their performanceby successfully passing tests required forthe most extreme conditions. (eg: salt mist,
damp or dry heat and cold environments)
per IEC 60068 standards.
In order to serve the worldwide marine
markets requirements, SNK products havethe following Marine certifications:
BV Marine, DNV, RINA, RMRS.

DNV

Rina

IECEx

1SNK160082S0201 - Rev. A

All SNK series products are suited to trackside fixed equipment.
For the more demanding environment ofrolling stock applications, PI-Spring has
been successfully tested in accordancewith IEC 61373 requirements to resist highvibration and shock conditions (multi-axial
waves, acceleration…).
The plastic material used is compliant
with the flammability, smoke toxicity andopacity severe requirements of the traction
segment and can be classified I2F2 per
NF F 16-101 and NF F 16-102 standards;
HL3 R22 per EN 45 545 standard and V0
per UL94 standard.
It complies with NFPA 130 per ASTM E 162
and ASTM E 662 standards tests and with
FR238.103 and BSS 7239 standards.

PAGE 11

Summary_2

2

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal blocks
PI-Spring technology
Technologies presentation		

14

Overview			

20

4 mm² / 10 AWG

6 mm² / 8 AWG
10 mm² / 6 AWG

16 mm² / 4 AWG

Ground
2.5 mm² / 12 AWG

4 mm² / 10 AWG

6 mm² / 8 AWG
10 mm² / 6 AWG
16 mm² / 4 AWG
Disconnect with blade
2.5 mm² / 12 AWG

Disconnect with plug
2.5 mm² / 12 AWG
For 5x20 fuses
2.5 mm² / 12 AWG
Double deck
2.5 mm² / 12 AWG

Triple deck
2.5 mm² / 12 AWG

Component holder
2.5 mm² / 12 AWG

ZK2.5		with 3 connections
ZK2.5-3P
ZK2.5-4P
with 4 connections
ZK4		
ZK4-3P
with 3 connections
ZK4-4P
with 4 connections
ZK6		
ZK6-3P
with 3 connections
ZK10		
ZK10-PV		
ZK10-3P
with 3 connections
ZK10-3P-PV
with 3 connections
ZK16		
ZK16-PV		ZK16-3P
with 3 connections
ZK16-3P-PV
with 3 connections

21
22
23
24
25
26
27
28
29
30
31
32
33
34
35

ZK2.5-PE		
ZK2.5-PE-3P
with 3 connections
ZP2.5-PE-4P
with 4 connections
ZK4-PE		ZK4-PE-3P
with 3 connections
ZK4-PE-4P
with 4 connections
ZK6-PE		ZK6-PE-3P
with 3 connections
ZK10-PE		
ZK10-PE-3P
with 3 connections
ZK16-PE		
ZK16-PE-3P
with 3 connections

37
38
39
40
41
42
43
44
45
46
47
48

ZK2.5-S
with test sockets
ZK2.5-S-4P
with test sockets
ZK2.5-S-R1		

49
50
51

ZK2.5-SP
ZK2.5-SP-4P

52
53

2

36

with test sockets
with test sockets

ZK2.5-SF 		
ZK2.5-SF-R
with blown fuse indicator

5455

ZK2.5-D2
ZK2.5-D1
ZK2.5-D2-PE
ZK2.5-D1-PE

2 feed-through circuits
1 feed-through circuit
1 feed-through circuit and 1 ground circuit
1 ground circuit

56
57
58
59

3 feed-through circuits
ZK2.5-T3
ZK2.5-T1
1 feed-through circuit
ZK2.5-L-L-PE 		
ZK2.5-L-N-PE
2 feed-through circuits and 1 ground circuit
ZK2.5-T1-PE
1 ground circuit

60
61
62
63
64

ZK2.5-CH-4P-LR		
ZK2.5-CH-4P-RL		
ZK2.5-D-CH-UD 		
ZK2.5-D-CH-DU		
ZK2.5-D-CH2-DU-RL		

65
66

67
68
69

PAGE 13

Summary_2

Feed-through
2.5 mm² / 12 AWG

PI-Spring technology - SNK series, terminal blocks
Features and benefits

The patented PI-Spring technology provides the benefits of bothPush-In and Spring technologies in one connection

2

Speed up your projects
50% faster connection time with Push-in mode
Our Push-in connection technology allows:
A direct one step insertion with rigid and prepared flexible
conductors.
Easy and quick insertion of the prepared flexible conductor
or rigid conductor.
Reduced effort and conductor preparation time with springmode– – Our connection requires minimal effort to insert wires withthe screwdriver– – Flexible conductors preparation is not necessary.
– – The screwdriver locks onto terminal freeing up hands.

Push-in mode

Spring mode

Clear circuit identification

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK162074S0201

Better project identification– – Circuit identification is improved thanks to the 20% larger
marking area
– – Pre-mark by hand or with label on our flat marking surface
and start immediately the wiring, before the final markers
mounting– – Spare markers re-printing in case of modifications.

PI-Spring technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process
Mounting, wiring, testing… made easy
Avoid mounting and wiring errors: asymmetrical design allows
immediate visual check in case of reversed terminal blocks.

2

Asymmetrical design avoids mounting error

Faster accessories mounting
Save up to 70% mounting time thanks to :–– screwless jumpers, component plugs, test devices, end
stops and snap-in ground terminal blocks.

Screwless accessories

Snap-in ground terminal blocks

1SNK162074S0201

Closed jumper location allows great stiffness of the terminal
block, avoid deflection while tightening and optimal jumper
guiding.

Closed jumper location for stiffness.

PAGE 15

PI-Spring technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart accessories
Flexible test solutions from individual insulated test adapter totest connectors for complete assemblies testing.
–– Direct plug-in into jumpers channels–– 5, 6, 8 mm spacing, mixing various spacing is possible–– 1000 V rating.

Plug-in individual test adapter.

Plug-in test connector.

Series plug associated with disconnect blocks.

Parallel plug to be installed between 2 blocks.

Pre-cut poles easy removable byhand.

Predefined shape to identify connected poles.

2

Component holder plugs for series or parallel component
mounting (resistors, filters, diodes...).
Can be installed after wiring.
Series plug offers screwless component connection(no soldering).

1SNK162074S0201

Smart plug-in jumpers:
Pre-cut poles removable by hand: clean cut.
Insulated up to 1000 V (avoid use of separators).
Predefined shapes in molding to easily identify connected
poles with a pen.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPI-Spring technology - SNK series, terminal blocks
Features and benefits

Optimized logistics
Reduce your accessories inventory by up to 50%
SNK PI-Spring, screw and pluggable ranges share the same
accessories.

– – All end sections and circuit separators fit several types andsizes of blocks– – One end section fits up to 21 models– – One circuit separator fits with 62 terminal blocks.

2

End sections and circuit separators fit several types and sizes of blocks

Shared accessories for SNK PI-Spring, screw and pluggable ranges

50% less inventory makes PI-Spring attractive to allworldwide markets–– The user selects one range but benefit from 2 connection
modes (push-in and spring) which have global certifications
and access to markets and applications worldwide–– Reduced packaging adapted to the usage (20 items
packaging on some items).
Push-in range + Spring range

Facilitate maintenance operations
Terminal blocks can be individually removed from a terminal
assembly equipped with markers: TE Connectivity markers
become independent after strip mounting. The markers remainon terminal in any situation.
Markers are interchangable: the smaller marker can fit
any bigger block.

PI-Spring

Reliable in harsh conditions
Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…
High corrosion resistance
PI-Spring clamp is made of high quality stainless steel.
Salt mist withstand up to 1,000 hours (as per IEC 60068).

RoHS
EAC

DNV

Rina
1SNK162074S0201

hazlocMaintenance operations facilitated

PAGE 17

SNK series, terminal blocks
PI-Spring technology - Range overview from 2.5 to 16 mm² – 12 to 4 AWG

22

3

Connections

Single deckFeed-throughGroundDisconnect
Fuse
Solar : 1500 VDC

Voltage test
screwdriver entry
point accepts
Category II probes

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Connections

Single deckFeed-throughGroundSolar: 1500 VDC

NEW

NEW

Double central channels
allows multiconfigurations(jumpering, testing and measuring)Connections

Single deckFeed-throughGroundDisconnect
Component holder

Two circuit
separators
for the entire
range

2x 2

Connections

Double deckFeed-throughGroundComponent holder

End section
can be used
as circuit separator

3x 2

Connections

Triple deckFeed-throughGround2

Rotating label
holdereasy plug-in injumper channel

1SNK162068S0201 - Rév. A

4

PAGE 19

SNK series, terminal blocks
PI-Spring technology

Feed-throughGroundComponent holder

Section
12 AWG
10 AWG
8 AWG
6 AWG

16 mm²

4 AWG

Double deck

ZK2.5
ZK2.5-3P
ZK4
ZK4-3P
ZK6
ZK6-3P
ZK10
ZK10-3P
ZK10-PV New ZK10-3P-PV
ZK16
ZK16-3P
ZK16-PV New ZK16-3P-PV

ZK2.5-4P
ZK4-4P

Feed-through

ZK2.5-PE
ZK4-PEZK6-PE
ZK10-PE

ZK2.5-PE-3P
ZK4-PE-3P
ZK6-PE-3P
ZK10-PE-3P

ZK16-PE

ZK16-PE-3P

ZK2.5-PE 4P
ZK4-PE- 4P

Ground

ZK2.5-CH-4P-LR ZK2.5-CH-4P-RL

Component holder

Section
2.5 mm²

12 AWG

ZK2.5-D2

Triple deck

ZK2.5-D1

ZK2.5-D2-PE

ZK2.5-D1-PE

ZK2.5-D-CH-UD

Feed-through

ZK2.5-D-CH-DU

ZK2.5-D-CH2-DU-RL

GroundSection
2.5 mm²

12 AWG

Disconnect

ZK2.5-T3

ZK2.5-T1

With blade

ZK2.5-L-L-PE
ZK2.5-L-N-PE

With plug

ZK2.5-T1-PE

For 5x20 mm fuses

Aligned with
ZK2.5-SF

Section
2.5 mm²

12 AWG

Clamp -

ZK2.5-S

ZK2.5-S-4P

Channels for jumpering or testing -Test socket -INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

ZK2.5-SP

ZK2.5-SP-4P

Blown-fuse indicator

ZK2.5-SF

ZK2.5-SF-R1
ZK2.5-SF-R3

ZK2.5-S-R1

1SNK162020S0201 - Rev. B

2

2.5 mm²4 mm²
6 mm²
10 mm²ZK2.5 PI-Spring terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

1SNK162052V0014

Ordering details
Description
Feed-throughColor
2 connections

Type

Grey
Blue
OrangeYellow
Green
Red
White
Black

ZK2.5

Part Number

ZK2.5
ZK2.5-BL
ZK2.5-OR
ZK2.5-YL
ZK2.5-GN
ZK2.5-RD
ZK2.5-WH
ZK2.5-BK

1SNK705010R0000
1SNK705020R0000
1SNK705030R0000
1SNK705060R0000
1SNK705061R0000
1SNK705062R0000
1SNK705065R0000
1SNK705066R0000

UL - CSARail

Main technical dataIEC41.7 1.64"

49.2 1.94"

50.9 2"

5.2 mm 0.205 in spacing

Weight(1 pce) g

50
50
50
50
50
50
50
50

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

2

Mounting instructions

Connecting capacity

24.6 0.97"

Pkg
qty

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Shield connectors
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey

White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
20
1960
22
20
10

5.30
1.80
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
4.10
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5

Green-yellow

Type
ZK2.5-PE

Part Number
1SNK705150R0000

Pkg

Weightqty(1 pce) g

20

10.00

Technical data valid for copper conductors only.

PAGE 21

1SNK162023S0201

1ZK2.5-3P PI-Spring terminal blocks
Feed-through with 3 connections - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Find all the features of the ZK2.5 terminal block with the added option of distributing or branching 3 conductors.

Ordering details
Description
3 connections

ZK2.5-3PPart Number

ZK2.5-3P
ZK2.5-3P-BL
ZK2.5-3P-OR
ZK2.5-3P-YL
ZK2.5-3P-GN
ZK2.5-3P-RD
ZK2.5-3P-WH
ZK2.5-3P-BK

Main technical data49.2 1.94"

64.7 2.55"

24.6 0.97"

5.2 mm 0.205 in spacing

1SNK705011R0000
1SNK705021R0000
1SNK705031R0000
1SNK705067R0000
1SNK705068R0000
1SNK705069R0000
1SNK705072R0000
1SNK705073R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
50
50
50

7.40
7.40
7.40
7.40
7.40
7.40
7.40
7.40

Mounting instructions

Connecting capacity

41.7 1.64"

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
1960
22
20
10

5.30
2.40
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-3PTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK2.5-PE-3P

Part Number
1SNK705151R0000

Pkg

Weightqty(1 pce) g

20

11.90

1SNK162024S0201

2

Type

Grey
Blue
OrangeYellow
Green
Red
White
Black

1SNK162061V0014

Feed-throughColorZK2.5-4P PI-Spring terminal blocks
Feed-through with 4 connections - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Find all the features of the ZK2.5 terminal block with the added option of distributing or branching 4 conductors.

Ordering details
1SNK162070V0014

Description
Feed-throughColor
4 connections

Type

Grey
Blue
OrangeYellow
Green
Red
White
Black

ZK2.5-4P

Part Number

ZK2.5-4P
ZK2.5-4P-BL
ZK2.5-4P-OR
ZK2.5-4P-YL
ZK2.5-4P-GN
ZK2.5-4P-RD
ZK2.5-4P-WH
ZK2.5-4P-BK

1SNK705012R0000
1SNK705022R0000
1SNK705032R0000
1SNK705074R0000
1SNK705075R0000
1SNK705076R0000
1SNK705079R0000
1SNK705080R0000

UL - CSARail

Main technical data

5.2 mm 0.205 in spacing

41.7 1.64"

49.2 1.94"
40.1 1.58"

Weight(1 pce) g

50
50
50
50
50
50
50
50

9.00
9.00
9.00
9.00
9.00
9.00
9.00
9.00

Mounting instructions

Connecting capacity

80.2 3.16"

Pkg
qty

IEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

2

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
1960
22
20
10

5.30
2.70
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-4P

Green-yellow

Type
ZK2.5-PE-4P

Part Number
1SNK705152R0000

Pkg

Weightqty(1 pce) g

20

13.60

Technical data valid for copper conductors only.

PAGE 23

1SNK162025S0201

1

ZK4 PI-Spring terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

10 AWG

1SNK162033V0014

Ordering details
Description
Feed-throughColor
2 connections

Grey
Blue
OrangeYellow
Red
Black

2
ZK4

Type

Part Number

ZK4
ZK4-BLZK4-ORZK4-YLZK4-RDZK4-BK

1SNK706010R0000
1SNK706020R0000
1SNK706030R0000
1SNK706060R0000
1SNK706062R0000
1SNK706066R0000

Main technical data

6 mm 0.236 in spacing

42.6 1.68"

50.1 1.97"
29 1.14"Weight(1 pce) g

50
50
50
50
50
50

7.90
7.90
7.90
7.90
7.90
7.90

Mounting instructions

Connecting capacity
55.3 2.18"

Pkg
qty

IEC

UL - CSA

Rail
Wire stripping
length1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)32 A / 4 mm²
480 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

30 A / 10 AWG
636 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

9

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
1680
22
20
10

5.30
1.80
1.30
2.10
2.90
3.60
7.40
38.10
2.80
3.80
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK4

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK4-PEPart Number
1SNK706150R0000

Pkg

Weightqty(1 pce) g

20

12.60

1SNK162026S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK4-3P PI-Spring terminal blocks
Feed-through with 3 connections - 6 mm 0.236 in spacing
Description

4 mm²

Find all the features of the ZK4 terminal block with the added option of distributing or branching 3 conductors.

10 AWG

Ordering details

1SNK162037V0014

Description
Feed-throughColor
3 connections

50.1 1.97"
29 1.14"6 mm 0.236 in spacing

42.6 1.68"

72.5 2.58"

Part Number

ZK4-3P
ZK4-3P-BL
ZK4-3P-OR

1SNK706011R0000
1SNK706021R0000
1SNK706031R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey
Blue
OrangeMain technical data

Pkg

Weightqty(1 pce) g

50
50
50

11.00
11.00
11.00

Mounting instructions

Connecting capacity
ZK4-3PType

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)32 A / 4 mm²
480 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

30 A / 10 AWG
636 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

9

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
1680
22
20
10

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
2.80
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK4-3P

Green-yellow

Type
ZK4-PE-3PPart Number
1SNK706151R0000

Pkg

Weightqty(1 pce) g

20

15.70

Technical data valid for copper conductors only.

PAGE 25

1SNK162027S0201

1

ZK4-4P PI-Spring terminal blocks
Feed-through with 4 connections - 6 mm 0.236 in spacing
Description

4 mm²

Find all the features of the ZK4 terminal block with the added option of distributing or branching 4 conductors.

10 AWG

Ordering details
1SNK162041V0014

Description
Feed-throughColor
4 connections

Type

Grey
Blue
OrangePart Number

ZK4-4P
ZK4-4P-BL
ZK4-4P-OR

Main technical data

1SNK706012R0000
1SNK706022R0000
1SNK706032R0000

IEC

UL - CSA

Rail
Wire stripping
length

ZK4-4P

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

50.1 1.97"
46.2 1.82"

6 mm 0.236 in spacing

42.6 1.68"

89.7 3.53"

Weight(1 pce) g

50
50
50

13.80
13.80
13.80

Mounting instructions

Connecting capacity

2

Pkg
qty

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)32 A / 4 mm²
480 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

30 A / 10 AWG
636 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

9

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
1680
22
20
10

5.30
2.70
1.30
2.10
2.90
3.60
7.40
38.10
2.80
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK4-4P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK4-PE-4PPart Number
1SNK706152R0000

Pkg

Weightqty(1 pce) g

20

18.40

1SNK162028S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK6 PI-Spring terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

6 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

8 AWG

1SNK162045V0014

Ordering details

ZK6

Description
Feed-through

Color

Type

2 connections

Grey
Blue
OrangeYellowRed
Black

Part Number

ZK6
ZK6-BLZK6-ORZK6-YLZK6-RDZK6-BK

1SNK708010R0000
1SNK708020R0000
1SNK708030R0000
1SNK708060R0000
1SNK708062R0000
1SNK708066R0000

Main technical data

8 mm 0.315 in spacing

43.4 1.71"

50.9 2"31 1.22"Weight(1 pce) g

50
50
50
50
50
50

11.80
11.80
11.80
11.80
11.80
11.80

2

Mounting instructions

Connecting capacity
57.5 2.26"

Pkg
qty

IEC

UL - CSA

Rail
Wire stripping
length1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1.5 mm²

24 ... 16 AWG

24 ... 10 AWG
24 ... 10 AWG

Tool (for flexible
conductor without
ferrule)41 A / 6 mm²
720 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

50 A / 8 AWG
1008 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 37 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

9

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
57 A (IEC)3 poles
57 A (IEC)57 A (IEC)4 poles
5 poles
57 A (IEC)57 A (IEC)
10 polesCross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.110 inSpacers
2.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
40
20
10
20
20
20
10
10
1680
22
20
10

5.30
1.80
2.70
4.10
5.60
7.00
14.20
2.80
3.80
1.70
2.40
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK6

Green-yellow

Type
ZK6-PEPart Number
1SNK708150R0000

Pkg

Weightqty(1 pce) g

20

20.30

Technical data valid for copper conductors only.

PAGE 27

1SNK162029S0201

1

ZK6-3P PI-Spring terminal blocks
Feed-through with 3 connections - 8 mm 0.315 in spacing
Description

6 mm²

Find all the features of the ZK6 terminal block with the added option of distributing or branching 3 conductors.

8 AWG

Ordering details

1SNK162049V0014

Description
Feed-throughColor
3 connections

Grey
Blue
Orange250.9 2"31 1.22"8 mm 0.315 in spacing

43.4 1.71"

79.1 3.12"

Part Number

ZK6-3P
ZK6-3P-BL
ZK6-3P-OR

Main technical data

1SNK708011R0000
1SNK708021R0000
1SNK708031R0000

Pkg

Weightqty(1 pce) g

50
50
50

16.70
16.70
16.70

Mounting instructions

Connecting capacity
ZK6-3PTypeIEC

UL - CSA

Rail
Wire stripping
length1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1.5 mm²

24 ... 16 AWG

24 ... 10 AWG
24 ... 10 AWG

Tool (for flexible
conductor without
ferrule)41 A / 6 mm²
720 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

50 A / 8 AWG
1008 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 37 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

9

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
57 A (IEC)3 poles
57 A (IEC)57 A (IEC)4 poles
5 poles
57 A (IEC)57 A (IEC)
10 polesCross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.110 inSpacers
2.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK6-3P
1SNK708911R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
40
20
10
20
20
20
10
10
1680
22
20
10

5.30
2.80
2.70
4.10
5.60
7.00
14.20
2.80
6.40
1.70
2.40
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK6-3P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK6-PE-3PPart Number
1SNK708151R0000

Pkg

Weightqty(1 pce) g

20

21.50

1SNK162030S0201

1

ZK10 PI-Spring terminal blocks
Feed-through - 10 mm 0.394 in spacing
Description

10 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.
1SNK162072V0014

6 AWG

Ordering details
Description
Feed-throughColor
2 connections

Type

Part Number

ZK10
ZK10-BL
ZK10-OR

1SNK710010R0000
1SNK710020R0000
1SNK710030R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey
Blue
OrangeMain technical data

ZK10

10 mm 0.394 in spacing

49 1.93"56.5 2.22"
46.2 1.82"

Weight(1 pce) g

20
20
20

27.20
27.20
27.20

Mounting instructions

Connecting capacity

82.5 3.25"

Pkg
qty

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 mm²

20 ... 12 AWG

20 ... 8 AWG
20 ... 8 AWG

Tool (for flexible
conductor without
ferrule)57 A / 10 mm²1200 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

55 A / 6 AWG
1596 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 51 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

4
5
6

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)76 A (IEC)4 poles
5 poles
76 A (IEC)76 A (IEC)
10 polesCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeDark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
JB10-2
1SNK910302R0000
JB10-3
1SNK910303R0000
JB10-4
1SNK910304R0000
JB10-5
1SNK910305R0000
JB10-10
1SNK910310R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
40
30
20
20
20
20
1680
22
20
10

5.30
3.30
4.60
7.10
9.40
12.00
24.00
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10

Green-yellow

Type
ZK10-PEPart Number
1SNK710150R0000

Pkg

Weightqty(1 pce) g

20

36.20

Technical data valid for copper conductors only.

PAGE 29

1SNK162031S0201

1

ZK10-PV PI-Spring terminal blocks
Feed-through - 12 mm 0.472 in spacing
Description

10 mm²

Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– Compatible with JB12 jumpers to interconnect multiple terminal blocks.
1SNK162124V0014

6 AWG

Ordering details
Description

Color
2 connections

1SNK710063R0000
1SNK710065R0000

IEC

UL - CSA

Rail

20 ... 6 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15
15 mm
0.591 inTool (for flexible
conductor without
ferrule)Flat screwdriverØ 4 mmØ 0.157 inMounting instructions

Connecting capacity

46.2 1.82"

12 mm 0.472 in spacing

49 1.93"56.5 2.22"

82.5 3.25"

Pkg Weight(1 pce) g
20
29.86
20
29.86

ZK10-PV
ZK10-PV-BL

Grey
Blue

Main technical data

ZK10-PV

Part Number

qty

Feed-through1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 8 AWG
20 ... 8 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 AWG

20 ... 12 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

57 A / 10 mm²1200 A

55 A / 6 AWG
1596 A
100 kA
1000 V AC / 1500 V DC 1000 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

3

5

Description

2

Color

Type

Part Number

Pkg

Weight

50
50
50
20
20
20
20
22
20
1680
10

5.30
4.90
7.60
12.90
6.40
1.70
2.40
10.00
14.00
0.273
0.20

qty

1
2

End stops
Jumper bars

3
4

Circuit separators
Test adapters

5

Terminal block
markers4

5.2 mm0.205 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank card

Dark grey
OrangeDark grey
Dark grey
White

Blank marker
Universal wire markers holder

Grey

BAZ1
JB12-2
JB12-3
JB12-5
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

1SNK900002R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000(1 pce) g

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may
modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK10-PEPart Number
1SNK710150R0000

Pkg

Weightqty(1 pce) g

20

36.20

1SNK162080S0201

2

Type

ZK10-3P PI-Spring terminal blocks
Feed-through with 3 connections - 10 mm 0.394 in spacing
Description

10 mm²–– Find all the features of the ZK10 terminal block with the added option of distributing or branching 3 conductors,–– ZK10-3P is perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC, 1000 V UL.

6 AWG

Ordering details
1SNK162095V0014

Description
Feed-throughColor
3 connections

10 mm 0.394 in spacing

49 1.93"56.5 2.22"
40.8 1.61"

1SNK710011R0000
1SNK710021R0000

IEC

UL - CSA

Rail
Wire stripping
lengthMain technical data

Pkg

Weightqty(1 pce) g

20
20

34.9
34.9

Mounting instructions

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 mm²

20 ... 12 AWG

96.3 3.79"

Part Number

ZK10-3P
ZK10-3P-BL

Grey
Blue

Connecting capacity
ZK10-3P

Type

20 ... 8 AWG
20 ... 8 AWG

Tool (for flexible
conductor without
ferrule)57 A / 10 mm²1200 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

56 A / 6 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 57 A - IM2 II 2 GD Ex eb I/II/IIIC

100 kA
1000 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)76 A (IEC)4 poles
5 poles
76 A (IEC)76 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card

Dark grey
Dark grey
OrangeDark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
JB10-2
1SNK910302R0000
JB10-3
1SNK910303R0000
JB10-4
1SNK910304R0000
JB10-5
1SNK910305R0000
JB10-10
1SNK910310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
40
30
20
20
20
1680
22
20
10

5.30
4.5
4.60
7.10
9.40
12.00
24.00
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10-3P

Green-yellow

Type
ZK10-PE-3P

Part Number
1SNK710151R0000

Pkg

Weightqty(1 pce) g

20

43.3

Technical data valid for copper conductors only.

PAGE 31

1SNK162061S0201

1

ZK10-3P-PV PI-Spring terminal blocks
Feed-through with 3 connections - 12 mm 0.472 in spacing

10 mm²

1SNK162126V0014

6 AWG

Description
Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– 3 connections configuration for easy grouping: 2 inputs / 1 output or 1 input / 2 outputs,–– Compatible with JB12 jumpers to interconnect multiple terminal blocks.
Description

Color

Feed-throughZK10-3P-PV

2

3 connections

Grey
Blue

Type

Part Number

Pkg Weightqty(1 pce) g

ZK10-3P-PV
ZK10-3P-PV-BL

1SNK710064R0000
1SNK710067R0000

20
20

Main technical data

Mounting instructions

Connecting capacity

40.8 1.61"

12 mm 0.472 in spacing

49 1.93"56.5 2.22"

96.3 3.79"

38.61
38.61

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

20 ... 6 AWG

Wire stripping
length15 mm
0.591 inTool (for flexible
conductor
without ferrule)

Flat screwdriverØ 4 mmØ 0.157 in

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 8 AWG
20 ... 8 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 AWG

20 ... 12 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

57 A / 10 mm²1200 A

56 A / 6 AWG
1596 A
100 kA
1000 V AC / 1500 V DC 1000 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2

4
3
4

5

Type

Part Number

Pkg

Weight

50
50
50
20
20
20
20
22
20
1680
10

5.30
4.90
7.60
12.90
6.40
1.70
2.40
10.00
14.00
0.273
0.20

qty

1
2
3

Color

5

End stops
Jumper bars

5.2 mm0.205 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)
0.118 inCircuit separators 3 mm
For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
Blank card
Terminal block

Dark grey
OrangeDark grey
Dark greyWhitemarkers
Blank marker
Universal wire markers holder

Grey

BAZ1
JB12-2
JB12-3
JB12-5
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

1SNK900002R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000(1 pce) g

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10-3P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK10-PE-3P

Part Number
1SNK710151R0000

Pkg

Weightqty(1 pce) g

20

43.3

1SNK162081S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify
the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK16 PI-Spring terminal blocks
Feed-through - 12 mm 0.472 in spacing
Description

16 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.
1SNK162075V0014

4 AWG

Ordering details
Description
Feed-through

Color

Type

2 connections

Part Number

ZK16
ZK16-BL

1SNK712010R0000
1SNK712020R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey
Blue

Main technical data
ZK16

12 mm 0.472 in spacing

49 1.93"56.5 2.22"
46.2 1.82"

Weight(1 pce) g

20
20

33.80
33.80

Mounting instructions

Connecting capacity

82.5 3.25"

Pkg
qty

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 6 mm²

20 ... 10 AWG

20 ... 6 AWG
20 ... 6 AWG

Tool (for flexible
conductor without
ferrule)76 A / 16 mm²
1920 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

75 A / 4 AWG
2544 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 69 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC ExATEX

Haz Loc

IECEx

BV

DNV

Accessories
Description

2
1
2
3

3

4
4
5

5

6

6

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)76 A (IEC)
5 polesCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeDark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
JB12-2
1SNK912302R0000
JB12-3
1SNK912303R0000
JB12-5
1SNK912305R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
20
20
20
20
1680
22
20
10

5.30
3.30
4.90
7.60
12.90
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16

Green-yellow

Type
ZK16-PEPart Number
1SNK712150R0000

Pkg

Weightqty(1 pce) g

20

47.00

Technical data valid for copper conductors only.

PAGE 33

1SNK162032S0201

1

ZK16-PV PI-Spring terminal blocks
Feed-through - 14 mm 0.551 in spacing
Description

16 mm²

Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– No available jumpers for ZK16-PV and ZK16-3P-PV (14 mm spacing).
1SNK162128V0014

4 AWG

Ordering details
Description

Color
2 connections

1SNK712063R0000
1SNK712065R0000

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

Wire stripping
length20 ... 6 AWG
20 ... 6 AWG

Flexible with twin ferrule

0.5 ... 6 AWG

20 ... 10 AWG

Grey
Blue

Main technical data

ZK16-PV

1 conductor per
clamp

14 mm 0.551 in spacing

49 1.93"56.5 2.22"
46.2 1.82"

2 conductors
per clamp

Pkg

Weightqty(1 pce) g

15
15

36.56
36.56

Mounting instructions

Connecting capacity

82.5 3.25"

Part Number

ZK16-PV
ZK16-PV-BL

Feed-throughTool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

76 A / 16 mm²
1920 A
1000 V AC / 1500 V DC
8000 VIP20

TH 35-7.5,
TH 35-15
15 mm
0.591 inFlat screwdriverØ 4 mmØ 0.157 in

75 A / 4 AWG
2544 A
100 kA
1000 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

3

Description

2

4

1
2
3

End stops
Circuit separators
Test adapters

4

Terminal block
markersColor
5.2 mm0.205 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank card

Type

Dark grey
Dark grey
Dark grey
White

Blank marker
Universal wire markers holder

Grey

BAZ1
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

Part Number
1SNK900002R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000

Pkg

Weightqty(1 pce)  g

50
20
20
20
22
20
1680
10

5.30
6.40
1.70
2.40
10.00
14.00
0.273
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify
the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK16-PEPart Number
1SNK712150R0000

Pkg

Weightqty(1 pce) g

20

47.00

1SNK162082S0201

2

Type

ZK16-3P PI-Spring terminal blocks
Feed-through with 3 connections - 12 mm 0.472 in spacing
Description

16 mm²–– Find all the features of the ZK16 terminal block with the added option of distributing or branching 3 conductors,–– ZK16-3P is perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC, 1000 V UL.

4 AWG

Ordering details
1SNK162098V0014

Description
Feed-throughColor
3 connections

49 1.93"56.5 2.22"
40.8 1.61"

12 mm 0.472 in spacing

1SNK712011R0000
1SNK712021R0000

IEC

UL - CSA

Rail
Wire stripping
lengthMain technical data

Pkg

Weightqty(1 pce) g

20
20

44.3
44.3

Mounting instructions

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 6 mm²

20 ... 10 AWG

98.3 3.87"

Part Number

ZK16-3P
ZK16-3P-BL

Grey
Blue

Connecting capacity
ZK16-3P

Type

20 ... 6 AWG
20 ... 6 AWG

Tool (for flexible
conductor without
ferrule)76 A / 16 mm²
1920 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

75 A / 4 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 76 A - IM2 II 2 GD Ex eb I/II/IIIC

100 kA
1000 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)76 A (IEC)
5 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card

Dark grey
Dark grey
OrangeDark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
JB12-2
1SNK912302R0000
JB12-3
1SNK912303R0000
JB12-5
1SNK912305R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
20
20
20
1680
22
20
10

5.30
4.5
4.90
7.60
12.90
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16-3P

Green-yellow

Type
ZK16-PE-3P

Part Number
1SNK712151R0000

Pkg

Weightqty(1 pce) g

20

56.65

Technical data valid for copper conductors only.

PAGE 35

1SNK162063S0201

1

ZK16-3P-PV PI-Spring terminal blocks
Feed-through with 3 connections - 14 mm 0.551 in spacing
Description

16 mm²

1SNK162130V0014

4 AWG

Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– 3 connections configuration for easy grouping: 2 inputs / 1 output or 1 input / 2 outputs,–– No available jumpers for ZK16-PV and ZK16-3P-PV (14 mm spacing).

Ordering details
Description

Color

Type

Part Number

Pkg Weight(1 pce) g
15
48.01
15
48.01
qty

3 connections

Feed-through2

ZK16-3P-PV
1SNK712064R0000
ZK16-3P-PV-BL 1SNK712067R0000

Grey
Blue

ZK16-3P-PV

Main technical data

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

20 ... 4 AWG

Wire stripping
length15 mm
0.591 inTool (for flexible

Flat screwdriverØ 4 mmØ 0.157 in

40.8 1.61"

14 mm 0.551 in spacing

1 conductor per
clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 6 AWG
20 ... 6 AWG

2 conductors per
clamp

Flexible with twin ferrule

0.5 ... 6 AWG

20 ... 10 AWG

49 1.93"56.5 2.22"

98.3 3.87"

76 A / 16 mm²
1920 A

75 A / 4 AWG
2544 A
100 kA
1000 V AC / 1500 V DC 1000 V
8000 V
IP20
NEMA 1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

conductor
without ferrule)

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

3

Description

2

4

1
2
3
4

Color

End stops
5.2 mm0.205 inCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Terminal block Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type
BAZ1
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

Part Number
1SNK900002R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
22
20
1680
10

5.30
6.40
1.70
2.40
10.00
14.00
0.273
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16-3P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK16-PE-3P

Part Number
1SNK712151R0000

Pkg

Weightqty(1 pce) g

20

56.65

1SNK162083S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-PE PI-Spring terminal blocks
Ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162081V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5.

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK2.5-PE

1SNK705150R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp

57.4 2.26"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length49.2 1.94"

5.2 mm 0.205 in spacing

41.7 1.64"

Tool (for flexible

24.6 0.97"

Weight(1 pce) g

20

10.00

Mounting instructions

Connecting capacity
ZK2.5-PEPkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
CS-R2
1SNK900106R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

5.30
1.80
3.80
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162039S0201

1

Technical data valid for copper conductors only.

PAGE 37

ZK2.5-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162069V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-3P.

Ordering details
Description

Color
3 connections

GroundTypePart Number

Green-yellow

ZK2.5-PE-3P

IEC

UL - CSA

Main technical data

ZK2.5-PE-3P

1SNK705151R0000

Rail

2

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthTool (for flexible

41.7 1.64"

49.2 1.94"

71.2 2.8"

Weight(1 pce) g

20

11.90

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

24.6 0.97"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

5.30
2.40
6.40
0.23
9.00
10.00
0.20

1SNK162040S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-PE-4P PI-Spring terminal blocks
Ground with 4 connections - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162032V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-4P.

Ordering details
Description
4 connections

Ground
ZK2.5-PE-4P

Color

Type

Part Number

Green-yellow

ZK2.5-PE-4P

1SNK705152R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp
41.7 1.64"

49.2 1.94"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthTool (for flexible
conductor without
ferrule)40.1 1.58"

5.2 mm 0.205 in spacing

Weight(1 pce) g

20

13.60

Mounting instructions

Connecting capacity
86.7 3.41"

Pkg
qty

Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

5.30
2.70
6.40
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162041S0201

1

Technical data valid for copper conductors only.

PAGE 39

ZK4-PE PI-Spring terminal blocks
Ground - 6 mm 0.236 in spacing
Description

4 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK4.
1SNK162036V0014

10 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK4-PE

1SNK706150R0000

IEC

UL - CSA

Rail

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

Wire stripping
lengthMain technical data
ZK4-PE

1 conductor
per clamp
62.7 2.47"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
26 ... 12 AWG

6 mm 0.236 in spacing

42.6 1.68"

Tool (for flexible

29 1.14"Weight(1 pce) g

20

12.60

Mounting instructions

Connecting capacity

50.1 1.97"

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
CS-R2
1SNK900106R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
1.80
3.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162042S0201

2

Pkg
qty

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK4-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 6 mm 0.236 in spacing
Description

4 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK4-3P.
1SNK162040V0014

10 AWG

Ordering details
Description

Color
3 connections

GroundTypePart Number

Green-yellow

ZK4-PE-3P

1SNK706151R0000

IEC

UL - CSA

Rail

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

Wire stripping
lengthMain technical data

ZK4-PE-3P

50.1 1.97"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
26 ... 12 AWG

42.6 1.68"

79 3.11"Weight(1 pce) g

20

15.70

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

29 1.14"6 mm 0.236 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
2.40
6.40
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162043S0201

1

Technical data valid for copper conductors only.

PAGE 41

ZK4-PE-4P PI-Spring terminal blocks
Ground with 4 connections - 6 mm 0.236 in spacing
Description

4 mm²

1SNK162044V0014

10 AWG

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK4-4P.

Ordering details
Description
4 connections

GroundZK4-PE-4P

ColorPart Number

Green-yellow

ZK4-PE-4P

IEC

UL - CSA

Rail

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

Wire stripping
lengthMain technical data

96.2 3.79"

42.6 1.68"

50.1 1.97"

1 conductor
per clamp

1SNK706152R0000

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)46.2 1.82"

6 mm 0.236 in spacing

Pkg

Weightqty(1 pce) g

20

18.40

Mounting instructions

Connecting capacity
2

Type

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
2.70
6.40
0.27
10.00
11.00
0.20

1SNK162044S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK6-PE PI-Spring terminal blocks
Ground - 8 mm 0.315 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK6.
1SNK162048V0014

8 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK6-PE

1SNK708150R0000

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp
64.6 2.54"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

24 ... 10 AWG
24 ... 10 AWG

50.9 2"8 mm 0.315 in spacing

43.4 1.71"

Tool (for flexible

31 1.22"Weight(1 pce) g

20

20.30

Mounting instructions

Connecting capacity

ZK6-PEPkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

8 AWG
1008 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
CS-R2
1SNK900106R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
1.80
3.80
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162045S0201

1

Technical data valid for copper conductors only.

PAGE 43

ZK6-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 8 mm 0.315 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK6-3P.
1SNK162082V0014

8 AWG

Ordering details
Description

Color
3 connections

GroundTypePart Number

Green-yellow

ZK6-PE-3P

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

Wire stripping
lengthMain technical data

ZK6-PE-3P

1SNK708151R0000

2

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

24 ... 10 AWG
24 ... 10 AWG

43.4 1.71"

50.9 2"

Weight(1 pce) g

20

21.50

Mounting instructions

Connecting capacity

85.6 3.37"

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

8 AWG
1008 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

31 1.22"8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK6-3P
1SNK708911R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
2.80
6.40
0.27
10.00
14.00
0.20

1SNK162046S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK10-PE PI-Spring terminal blocks
Ground - 10 mm 0.394 in spacing
Description

10 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK10.
1SNK162083V0014

6 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK10-PE

1SNK710150R0000

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

Wire stripping
lengthMain technical data

ZK10-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 8 AWG
20 ... 8 AWG

Tool (for flexible

49 1.9"56.5 2.2"

87.7 3.45"

Weight(1 pce) g

20

36.20

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

46.2 1.18"

10 mm 0.394 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

5

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
20
1680
22
20
10

5.30
3.30
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162047S0201

1

Technical data valid for copper conductors only.

PAGE 45

ZK10-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 10 mm 0.394 in spacing
Description

10 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 standard,–– Secured snap on or off the rail,–– Profile aligned with ZK10-3P.
1SNK162097V0014

6 AWG

Ordering details
Description

Color
3 connections

GroundType

Green-yellow

ZK10-PE-3P

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

Wire stripping
lengthMain technical data

ZK10-PE-3P

Part Number
1SNK710151R0000

2

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 8 AWG
20 ... 8 AWG

49 1.93"56.5 2.22"

Weight(1 pce) g

20

43.3

Mounting instructions

Connecting capacity

99.1 3.87"

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC

TH 35-7.5,
TH 35-15
15 mm
0.591 inFlat screwdriverØ 4 mmØ 0.157 in

40.8 1.61"

10 mm 0.394 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories
1

3

Description

2
1
2
3

End stops
End sections
Test adapters

4

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
1680
22
20
10

5.30
4.5
1.70
2.40
0.27
10.00
14.00
0.20

1SNK162062S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK16-PE PI-Spring terminal blocks
Ground - 12 mm 0.472 in spacing
Description

16 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK16.
1SNK162084V0014

4 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK16-PE

1SNK712150R0000

IEC

UL - CSA

Rail

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

Wire stripping
lengthMain technical data

ZK16-PE56.5 2.22"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 6 AWG
20 ... 6 AWG

49 1.93"87.7 3.45"

Weight(1 pce) g

20

47.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG
2544 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

46.2 1.82"

12 mm 0.472 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

5

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
20
1680
22
20
10

5.30
3.30
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162048S0201

1

Technical data valid for copper conductors only.

PAGE 47

ZK16-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 12 mm 0.472 in spacing
Description

16 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 standard,–– Secured snap on or off the rail,–– Profile aligned with ZK16-3P.
1SNK162100V0014

4 AWG

Ordering details
Description

Color
3 connections

GroundType

Green-yellow

ZK16-PE-3P

IEC

UL - CSA

Rail

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

Wire stripping
lengthMain technical data

ZK16-PE-3P

Part Number
1SNK712151R0000

2

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 6 AWG
20 ... 6 AWG

49 1.93"56.5 2.22"
40.8 1.61"

Weight(1 pce) g

20

56.65

Mounting instructions

Connecting capacity
101.1 3.98"

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG
2544 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC

TH 35-7.5,
TH 35-15
15 mm
0.591 inFlat screwdriverØ 4 mmØ 0.157 in

12 mm 0.472 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories
1

3

Description

2
1
2
3

End stops
End sections
Test adapters

4

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
1680
22
20
10

5.30
4.5
1.70
2.40
0.27
10.00
14.00
0.20

1SNK162064S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-S PI-Spring terminal blocks
Disconnect with blade - with test sockets - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162085V0014

12 AWG

Description
Combine high performance with compact dimensions: 630 V IEC 300 V UL.
Secure the current measurement:–– for currents below 50 mA, thanks to 2 built in test points DIA 2 mm 0.079 in,–– for currents up to 16 A, by using the TP4 test adapter inserted into the jumper channels.

Ordering details
Description

Colorwith 2 test sockets DIA 2 mm
0.079 in

Disconnect

Type

Grey
Blue
Orange

ZK2.5-S
ZK2.5-S-BL
ZK2.5-S-OR

1SNK705310R0000
1SNK705320R0000
1SNK705330R0000

UL - CSARail

Main technical data

5.2 mm 0.205 in spacing

60.1 2.37"
52.6 2.07"

53.3 2.1"
45.8 1.8"
27.9 1.10"

IEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

65.7 2.59"

Pkg

Weightqty(1 pce) g

50
50
50

8.10
8.10
8.10

Mounting instructions

Connecting capacity

ZK2.5-SPart Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

20 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mounted with
fixed foot on top (power side) so that the disconnect knife does not partially close through gravity. Furthermore,as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary disconnection
at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in0.079 in
2 mm
32 A (IEC)2 poles
3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Shield connectors
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
20
1960
22
20
10

5.30
2.40
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
4.10
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162036S0201

1

Technical data valid for copper conductors only.

PAGE 49

ZK2.5-S-4P PI-Spring terminal blocks
Disconnect with blade - with test socket - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162103V0014

12 AWG

ZK2.5-S-4P

Description–– Combine high performances with compact dimensions: 630 V IEC 300 V UL,–– Simplify the measurement with 1 built in test point DIA 2 mm 0.079 in (for current below 50mA) and TP... test
adapter inserted into one jumper channel,–– Clear marking visibility with SNK top marking location 20% enlarged.

Ordering details
Description

Colorwith 1 test socket DIA 2 mm
0.079 in

Disconnect

Type

Grey
Blue
Orange

ZK2.5-S-4P
ZK2.5-S-4P-BL
ZK2.5-S-4P-OR

Main technical data

53.2 2.1"
45.8 1.8"
59.5 2.34"
52 2.05"

86.1 3.39"

38.8 1.53"

5.2 mm 0.205 in spacing

1SNK705312R0000
1SNK705321R0000
1SNK705331R0000

Pkg

Weightqty(1 pce) g

50
50
50

11.14
11.14
11.14

Mounting instructions

Connecting capacity

2

Part NumberIEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

20 A / 2.5 mm²
300 A

20 A / 12 AWG

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mounted with
fixed foot on top (power side) so that the disconnect knife does not partially close through gravity. Furthermore,as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary disconnection
at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

Accessories
1

Description

2
1
2
3

3

4

5

6

7

4
5
6
7

Color

5.2 mm0.205 in
0.158 in
2 mm
32 A (IEC)2 poles
3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

1SNK162069S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-S-R1 PI-Spring terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing
Description

2.5 mm²

Simplify the distribution of circuits in marshalling cabinets thanks to our disconnect terminal blocks with thesame profile as ZK2.5-SF fuse.

12 AWG

Ordering details
Description

1SNK162088V0014

55.4 2.18"

48.6 1.91"

62.9 2.48"

56.1 2.21"
24.6 0.97"

Part Number

ZK2.5-S-R1

1SNK706310R0000

UL - CSA

Rail

Pkg

Weightqty(1 pce) g

50

8.90

Mounting instructions

Connecting capacity

2 conductors
per clamp

6 mm 0.236 in spacing

Grey

Main technical data
1 conductor
per clamp

63.1 2.48"

Type

Profile aligned with ZK2.5-SF

Disconnect

ZK2.5-S-R1

Color

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthFlexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

2

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

20 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mounted with
fixed foot on top (power side) so that the disconnect knife does not partially close through gravity. Furthermore,as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary disconnection
at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
20
20
20
10
10
1680
22
20
10

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

PI-Spring terminal blocks
Description

ZK4-3P

ZK2.5-SF

Feed-through
Fuse

Color
Grey
Grey, dark grey

Type
ZK4-3P
ZK2.5-SF

Part Number
1SNK706011R0000
1SNK706410R0000

Pkg

Weightqty(1 pce) g

50
50

11.00
16.20

Technical data valid for copper conductors only.

PAGE 51

1SNK162037S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-SP PI-Spring terminal blocks
Disconnect with plug - with test sockets - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
The flexible solution for fitting the component of your choice in series with our quick-fitting PG5 component
holder plug:–– compatible with components of 8.8 x 3.2 mm 0.346 x 0.125 in, such as resistors, diodes or mini axial fuses.

1SNK162089V0014

Ordering details
Description

Colorwith 2 test sockets DIA 2 mm
0.079 in

Disconnect

Grey

ZK2.5-SP43.1 1.69"

50.6 1.99"

65.7 2.59"

ZK2.5-SP

Main technical data

Part Number
1SNK705311R0000

Pkg

Weightqty(1 pce) g

50

11.50

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

17 A / 2.5 mm²
300 A

18 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 127.9 1.10"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
0.118 in4 Circuit separators 3 mm
5 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
6 Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
7 Shield connectors
8 Component plugs Components in series with circuit
9 Disconnect plugs Equipped with linking bar
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Dark grey
Orange
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
20
20
20
1960
22
20
10

5.30
2.40
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
4.10
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK162038S0201

2

Type

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-SP-4P PI-Spring terminal blocks
Disconnect with plug - with test socket - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
The flexible solution for fitting the component of your choice in series with our quick-fitting PG5 component
holder plug:–– compatible with components of 8.8 x 3.2 mm 0.346 x 0.125 in, such as resistors, diodes or mini axial fuses.

1SNK162106V0014

Ordering details
Description

Color

Type

with 1 test socket DIA 2 mm
0.079 in

Disconnect

Grey

ZK2.5-SP-4P

1SNK705313R0000

UL - CSARail

Main technical data

50.6 1.99"
43.1 1.7"
38.8 1.53"

5.2 mm 0.205 in spacingIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

86.1 3.39"

Pkg

Weightqty(1 pce) g

50

10.67

Mounting instructions

Connecting capacity

ZK2.5-SP-4P

Part Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

17 A / 2.5 mm²
300 A

18 A / 12 AWG

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Component plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
20
20
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162070S0201

9

Color

Technical data valid for copper conductors only.

PAGE 53

ZK2.5-SF PI-Spring terminal blocks
For 5x20 fuses - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description
Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the 2 jumper channels aligned with ZK4-3P feed-through and ZK2.5-S-R1
disconnect terminal blocks.

Ordering details
1SNK162090V0014

Description

Color

Fuse

Type

Grey, dark grey

ZK2.5-SFIEC

UL - CSA

Main technical data

74 2.91"

81.5 3.21"

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-SF

63.1 2.48"

1SNK706410R0000

Pkg

Weightqty(1 pce) g

50

16.20

Mounting instructions

Connecting capacity
2

Part Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

6.3 A / 2.5 mm²

16 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The fuse holder must be first disconnected prior any fuse replacement. Mount your fuse safely without touching
any active part: put the fuse into the hooks of the fuse holder shutter; at the closing of the shutter, the fuse isperfectly in place in the fuse holder.
24.6 0.97"

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

6 mm 0.236 in spacing

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

1

3

4

5

6

7

Description

2

8

1
2
3

4
5
6
7
8

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
20
20
20
10
10
1680
22
20

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK162021S0201

Accessories

ZK2.5-SF-R PI-Spring terminal blocks
For 5x20 fuses - with blown fuse indicator - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the 2 jumper channels aligned with ZK4-3P feed-through and ZK2.5-S-R1
disconnect terminal blocks,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

1SNK162091V0014

Ordering details
Description

Color

Type

Fuse with blown fuse indicator 24 ... 110 V AC / DC Grey, dark greywith blown fuse indicator 115 ... 250 V AC / DC

ZK2.5-SF-R1
ZK2.5-SF-R3

1SNK706411R0000
1SNK706412R0000

UL - CSARail

Main technical data

Pkg

Weightqty(1 pce) g

50
50

16.30
16.30

Mounting instructions

Connecting capacity
ZK2.5-SF-R

Part NumberIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

24.6 0.97"

6 mm 0.236 in spacing

74 2.91"

81.5 3.21"

63.1 2.48"

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

6.3 A / 2.5 mm²

16 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 VIP20

300 V

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The fuse holder must be first disconnected prior any fuse replacement. Mount your fuse safely without touching
any active part: put the fuse into the hooks of the fuse holder shutter; at the closing of the shutter, the fuse isperfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

1

3

4

5

6

7

Description

2

8

1
2
3

4
5
6
7
8

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
41 A (IEC)
50 polesCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
20
20
20
10
10
1680
22
20

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

PAGE 55

1SNK162022S0201

Accessories

ZK2.5-D2 PI-Spring terminal blocks
Double deck with 2 feed-through circuits - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Combine high performance with compact dimensions:–– 800 V IEC 600 V UL,–– 2 jumper channels and a large input and output marker zone on each deck.

Ordering details
1SNK162060V0014

Description
Feed-throughColor
2 feed-through circuits

Grey
Blue

ZK2.5-D2

44.6 1.76"

5.2 mm 0.205 in spacing

61.7 2.43"

69.2 2.72"

78.5 3.09"

Part Number

ZK2.5-D2
ZK2.5-D2-BL

Main technical data

1SNK705210R0000
1SNK705220R0000

Pkg

Weightqty(1 pce) g

50
50

11.20
11.20

Mounting instructions

Connecting capacity
2

Type

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC ExATEX

Haz Loc

IECEx

BV

DNV

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-D2 and ZK2.5-D1

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZK2.5-D1-PE

Part Number
1SNK705250R0000

Pkg

Weightqty(1 pce) g

20

15.70

1SNK162033S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-D1 PI-Spring terminal blocks
Double deck with 1 feed-through circuit - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Find the same functionalities as ZK2.5-D2 and ease one potential distribution on 4 independent connections.

Ordering details
Description

1SNK162078V0014

Feed-through

ZK2.5-D1

61.7 2.43"

69.2 2.72"

78.5 3.09"

Color

Type

1 feed-through circuit

Grey

Part Number

ZK2.5-D1

1SNK705211R0000

UL - CSARail

Main technical data

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacityIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

2
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

44.6 1.76"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-D2 and ZK2.5-D1

Green-yellow

Type
ZK2.5-D1-PE

Part Number
1SNK705250R0000

Pkg

Weightqty(1 pce) g

20

15.70

Technical data valid for copper conductors only.

PAGE 57

1SNK162035S0201

1ZK2.5-D2-PE PI-Spring terminal blocks
Double deck with 1 feed-through circuit and 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162079V0014

12 AWG

Description
Combine high performance with compact dimensions:–– 800 V IEC 600 V UL,–– 1 feed through circuit and 1 ground circuit in just 5.2 mm 0.205 in spacing,–– 2 jumper channels and a large input and output marker zone on each deck,–– designed for easy wiring.

Ordering details
Description

Color

Feed-through + 1 feed-through circuit and 1 groundcircuitgroundTypePart Number

Grey,Green-yellow

ZK2.5-D2-PE

IEC

UL - CSA

Main technical data

44 1.73"

5.2 mm 0.205 in spacing

61.7 2.43"

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

84.6 3.33"

Weight(1 pce) g

20

15.70

Mounting instructions

Connecting capacity

ZK2.5-D2-PE

69.2 2.72"

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

800 V
8000 VIP20

600 V

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

IECEx

ATEX

Haz Loc

BV

DNV

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through PI-Spring terminal blocks
Description
Feed-throughTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color

Type
Grey

ZK2.5-D2

Part Number
1SNK705210R0000

Pkg

Weightqty(1 pce) g

50

11.20

1SNK162034S0201

2

1SNK705212R0000

Pkg
qty

ZK2.5-D1-PE PI-Spring terminal blocks
Double deck with 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162080V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-D2.

Ordering details
DescriptionColor
1 ground circuit

GroundTypePart Number

Green-yellow

ZK2.5-D1-PE

1SNK705250R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp
84.6 3.33"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length

5.2 mm 0.205 in spacing

61.7 2.43"

69.2 2.72"

Tool (for flexible

44 1.73"

Weight(1 pce) g

20

15.70

Mounting instructions

Connecting capacity
ZK2.5-D1-PE

Pkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

5

7

Description

2
1
2
3

End stops
End sections
Test adapters

4

Test connectors

5
6
7

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

4

6

Color
10 mm
0.394 in
2 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Universal wire markers holder

Dark grey
Dark grey
Dark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162049S0201

1

Technical data valid for copper conductors only.

PAGE 59

ZK2.5-T3 PI-Spring terminal blocks
Triple deck with 3 feed-through circuits - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Combine high performance with compact dimensions in just 5.2 mm 0.205 in spacing:–– 500 V IEC 300 V UL,–– 1 jumper channel and a large input and output marker zone on each deck.

Ordering details
1SNK162109V0014

Description

2

Feed-through74.7 2.91"

82.2 3.22"

Type

3 feed-through circuits

Grey

ZK2.5-T3

Main technical data

Part Number
1SNK705510R0000

Pkg

Weightqty(1 pce) g

25

17.33

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-T3

99.6 3.89"

Color

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.9 1.73"

CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

5.2 mm 0.205 in spacing

Accessories
1

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Ground PI-Spring terminal blocks
Description
GroundTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

ColorGreen-yellow

Type
ZK2.5-T1-PE

Part Number
1SNK705550R0000

Pkg

Weightqty(1 pce) g

25

21.53

1SNK162075S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-T1 PI-Spring terminal blocks
Triple deck with 1 feed-through circuit - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Find the same functionalities as ZK2.5-T3 and ease one potential distribution on 6 independent connections.

Ordering details
Description

1SNK162110V0014

Feed-through

ZK2.5-T1

74.7 2.91"

82.2 3.22"

99.6 3.89"

Color

Type

1 feed-through circuit

Grey

Part Number

ZK2.5-T1

1SNK705511R0000

UL - CSARail

Main technical data

Pkg

Weightqty(1 pce) g

25

17.33

Mounting instructions

Connecting capacityIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

44.9 1.73"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Green-yellow

Type
ZK2.5-T1-PE

Part Number
1SNK705550R0000

Pkg

Weightqty(1 pce) g

25

21.53

Technical data valid for copper conductors only.

PAGE 61

1SNK162076S0201

1ZK2.5-L-L-PE PI-Spring terminal blocks
Triple deck with 2 feed-through circuits and 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162112V0014

12 AWG

Description
Combine high performance with compact dimensions:–– 500V IEC 300 V UL,–– 2 feed through circuits and 1 ground circuit in just 5.2 mm 0.205 in spacing,–– 1 jumper channel and a large input and output marker zone on each deck,–– designed for easy wiring.

Ordering details
Description

Color

Feed-through + 2 feed-through circuits and 1
ground circuit
groundType

Grey,Green-yellow

ZK2.5-L-L-PE

IEC

UL - CSA

Main technical data
ZK2.5-L-L-PE

5.2 mm 0.205 in spacing

74.7 2.91"

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

101.9 3.97"

44.9 1.73"

1SNK705512R0000

Pkg

Weightqty(1 pce) g

25

21.38

Mounting instructions

Connecting capacity

82.2 3.22"

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

IECEx

ATEX

BV

Accessories
1

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through PI-Spring terminal blocks
Description
Feed-throughTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color

Type
Grey

ZK2.5-T3

Part Number
1SNK705510R0000

Pkg

Weightqty(1 pce) g

25

17.33

1SNK162078S0201

2

Part Number

ZK2.5-L-N-PE PI-Spring terminal blocks
Triple deck with 2 feed-through circuits and 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162113V0014

12 AWG

Description
Combine high performance with compact dimensions:–– 500 V IEC 300 V UL,–– 2 feed through circuits, phase and neutral, and 1 ground circuit in just 5.2 mm 0.205 in spacing,–– 1 jumper channel and a large input and output marker zone on each deck,–– designed for easy wiring.

Ordering details
Description

Color

Feed-through + 2 feed-through circuits and 1
ground circuit
groundTypeBlue, grey,
Green-yellow

ZK2.5-L-N-PE

1SNK705513R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

44.9 1.73"

5.2 mm 0.205 in spacing

74.7 2.91"

82.2 3.22"

101.9 3.97"

Pkg

Weightqty(1 pce) g

25

21.38

Mounting instructions

Connecting capacity

ZK2.5-L-N-PE

Part Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

IECEx

ATEX

BV

Accessories

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through PI-Spring terminal blocks
Description
Feed-through

Color

Type
Grey

ZK2.5-T3

Part Number
1SNK705510R0000

Pkg

Weightqty(1 pce) g

25

17.33

Technical data valid for copper conductors only.

PAGE 63

1SNK162079S0201

1ZK2.5-T1-PE PI-Spring terminal blocks
Triple deck with 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162111V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-T3,–– 1 jumper channel on bottom and middle decks.

Ordering details
DescriptionColor
1 ground circuit

GroundType

Green-yellow

ZK2.5-T1-PE

IEC

UL - CSA

Main technical data
ZK2.5-T1-PE

1 conductor
per clamp
101.9 3.97"

1SNK705550R0000

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

RailWire stripping
length

5.2 mm 0.205 in spacing

74.7 2.91"

Tool (for flexible

44.9 1.73"

Pkg

Weightqty(1 pce) g

25

21.53

Mounting instructions

Connecting capacity

82.2 3.22"

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Test adapters

4

Test connectors

5
6

Label holders
Terminal block
markers

4

6

Color
10 mm
0.394 in
0.8 mm
0.031 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
Dark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162077S0201

2

Part Number

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-CH-4P-LR PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuit with one 1N4007 diode,–– Clear identification of the diode orientation with marking identification on the top of the terminal block

1SNK162107V0014

Ordering details
Description

Colorwith 1 test socket DIA 2 mm
0.079 inComponent
holderGrey

ZK2.5-CH-4P

50.6 1.99"
43.1 1.7"

1SNK705710R0000

UL - CSA

Rail

Pkg

Weightqty(1 pce) g

50

10.91

Mounting instructions
IEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

86.1 3.39"

38.8 1.53"

Part Number

ZK2.5-CH-4P-LR

Main technical data
Connecting capacity

5.2 mm 0.205 in spacingTypeconductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 A / 2.5 mm²

1 A / 12 AWG

630 V

300 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3
4

5

6

7

4
5
6
7

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162071S0201

3

Color

Technical data valid for copper conductors only.

PAGE 65

ZK2.5-CH-4P-RL PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuit with one 1N4007 diode,–– Clear identification of the diode orientation with marking identification on the top of the terminal block

1SNK162108V0014

Ordering details
Description

Colorwith 1 test socket DIA 2 mm
0.079 inComponent
holderGrey

ZK2.5-CH-4P

50.6 1.99"
43.1 1.7"
38.8 1.53"

Part Number
1SNK705711R0000

Pkg

Weightqty(1 pce) g

50

10.91

Mounting instructions
IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

86.1 3.39"

5.2 mm 0.205 in spacing

ZK2.5-CH-4P-RL

Main technical data
Connecting capacity

2

Type

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 A / 2.5 mm²

1 A / 12 AWG

630 V

300 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

4
5
6
7

Color

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

1SNK162072S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-D-CH-UD PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details

1SNK162101V0014

Description
Component
holder2 conductors
per clamp

61.7 2.43"

Grey

Part Number

ZK2.5-D-CH-UD

1SNK705213R0000

UL - CSA

Rail

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacity

ZK2.5-D-CH

69.2 2.72"

Type

Main technical data
1 conductor
per clamp

78.5 3.09"

Color

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthFlexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

2

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A

20 A / 12 AWG

800 V

600 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.443 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.6 1.76"

CE

RoHS

USR CNR

CSA

EAC

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162066S0201

1

Technical data valid for copper conductors only.

PAGE 67

ZK2.5-D-CH-DU PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details

1SNK162102V0014

Description
Component
holder

61.7 2.43"

Grey

ZK2.5-D-CH-DU

Part Number
1SNK705214R0000

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-D-CH

69.2 2.72"

Type

Main technical data

2

78.5 3.09"

Color

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A

20 A / 12 AWG

800 V

600 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.443 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.6 1.76"

CE

RoHS

USR CNR

CSA

EAC

5.2 mm 0.205 in spacing

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

1SNK162067S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZK2.5-D-CH2-DU-RL PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuit with 1N4007 diodes;–– Convenient identification of the diodes orientation on the terminal block front side.

Ordering details

1SNK162114V0014

Description
Component
holder

61.7 2.43"

69.2 2.72"
44.6 1.76"

Type
ZK2.5-D-CH2-DU-RL

GreyMain technical data

Part Number
1SNK705219R0000

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-D-CH2

78.5 3.09"

Color

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 A / 2.5 mm²/ 12 AWG

800 V

600 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.443 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing

CE

RoHS

EAC

Accessories

3

4

5

6

7

Description

2

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7

Shield connectors
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162073S0201

1

Technical data valid for copper conductors only.

PAGE 69

Summary_3

3

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal blocks
Screw clamp technology
Technologies presentation			
Overview				

72
76

Feed-through4 mm² / 12 AWG
6 mm² / 10 AWG

ZS4			
80
ZS6			
81
ZS6-3S and ZS6-4S		
with 3 and 4 connections
82-83
ZS10			10 mm² / 6 AWG
84
16 mm² / 4 AWG
ZS16			85ZS25			25 mm² / 3 AWG
86
35 mm² / 0 AWG
ZS35			8750 mm² / 0 AWG
ZS50			88ZS70			70 mm² / 00 AWG
89
95 mm² / 0000 AWG ZS95			
90
150 mm² / 350 Kcmil ZS150			
91
92
240 mm² / 240 Kcmil ZS240			
ZS4-PE			ZS6-PE			
ZS6-3S-PE and ZS6-4S-PE
with 3 and 4 connections
ZS10-PE			
10 mm² / 6 AWG
16 mm² / 4 AWG
ZS16-PE			
ZS25-PE			
25 mm² / 3 AWG
35 mm² / 2 AWG
ZS35-PE			
35 mm²
ZS35-PEN		+ neutral
ZS50-PE			
50 mm² / 0 AWG
70 mm² / 00 AWG
ZS70-PE			
95 mm² / 0000 AWG ZS95-PE			
Disconnect with blade
4 mm² / 10 AWG
ZS4-S, ZS4-S-T, ZS4-S-R1 and ZS4-S-T-R1
6 mm² / 10 AWG
ZS6-S and ZS6-S-4S-T
10 mm² / 6 AWG
ZS10-S			

with testwith test

Disconnect with plug
ZS4-SP, ZS4-SP-T2, ZS4-SP-R1 and ZS4-SP-T2-R1 with test
4 mm² / 10 AWG
ZS10-SP			
10 mm² / 6 AWG
Fuse and marshalling cabinets application overview		

93
94
95-96
97
98
99
100
101
102
103
104
105-108
109-110111
112-115
116
118

For 5x20 and 5x25 mm fuses
ZS4-SF1 and ZS4-SF1-T
4 mm² / 10 AWG
with test
ZS4-SF1-R		
with fuse indicator and test
ZS4-R1		feed-throughZS4-S-R3		
disconnect with lever120-121122-123124
125

For 5x20 mm fuses and marshalling cabinets application
4 mm² / 10 AWG
ZS4-SF			
ZS4-SF-T
with test 		ZS4-SF-R
with fuse indicator and test
ZS4-R2feed-throughZS4-PE-R2
ground 		ZS4-S-R2
disconnect with lever

126
127
128-129
130
131
132

For 6.3x32 mm fuses (¼ x 1¼ in)
10 mm² / 6 AWG
ZS10-SF			ZS10-SF-R
with fuse indicator
ZS10-S-R2
disconnect with lever
Double deck
4 mm² / 12 AWG
6 mm² / 10 AWG

133
134
135

ZS4-D2 and ZS4-D1
ZS6-D2 and ZS6-D1
ZS6-D2-PE
ZS6-D1-PE
ZS4-D2-S
ZS4-D2-S-T
ZS4-D2-SF1
ZS4-D2-SF1-R

2 and 1 feed-through circuits
136-137
2 and 1 feed-through circuits
138-139
1 feed-through circuit and 1 ground circuit
140
1 ground circuit
141
1 disconnect circuit and 1 feed-through circuit
142
1 disconnect circuit + test and 1 feed-through circuit
143
1 fuse circuit and 1 feed-through circuit
144
1 fuse circuit + fuse indicator and 1 feed-through circuit
145

Triple deck
4 mm² / 12 AWG
4 mm² / 10 AWG

ZS4-T3ZS4-T3-R1

3 feed-through circuits
3 feed-through circuits

Component holder
4 mm² / 12 AWG

ZS4-D-CH-UD and ZS4-D-CH-DU

4 mm² / 10 AWG

Test and measurement
Overview				
10 mm² / 6 AWG
ZS10-ST			
ZS10-ST-1
for Potential Transformer circuits
ZS10-ST-T4
for Current Transformer circuits
ZS10-R1
feed-throughZS10-PE-R1
ground		

3

146
147
148-149
150
154
155
156
157
158

PAGE 71

Summary_3

Ground4 mm² / 12 AWG
6 mm² / 10 AWG

Screw clamp technology - SNK series, terminal blocks
Features and benefits

TE Connectivity screw clamp technology benefits from 60 yearsof experience.

3

Speed up your projects
An optimized conductor guiding
Smooth connection process up to 2 conductors with orwithout ferrules thanks to funnel entry shape.
Also perfectly adapted to double ferrule shape 1

1Security: flap avoiding the insertion of cable underneath theclamp 2 .

2

Better project identification– – Circuit identification is improved thanks to the 20% larger
marking area
– – Pre-mark by hand or with label on our flat marking surface
and start immediately the wiring, before the final markers
mounting– – Spare markers re-printing in case of modifications.
Clear circuit identification

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161092S0201

Engineered conductor entry

Screw clamp technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process.
Mounting, wiring, testing… made easy.
Avoid mounting and wiring errors: asymmetrical design allows
immediate visual check in case of reversed terminal blocks.

Asymmetrical design avoids mounting error

3

Minimize retightening campaigns
High torque resistance : the clamp is punched to increase thenumber of threads in contact by 30 % 1 .
The TE Connectivity exclusive anti-release system createsa controlled locking-screw effect reinforced by the 2
overlapping tabs that maintain the clamp parts 2 .
1

2High torque resistanceAnti-release system

Screwless accessories

Snap-in ground terminal block for
rapid installation

PAGE 73

1SNK161092S0201

Faster accessories mounting
Save up to 70% mounting time thanks to screwless accessories: jumpers, component plugs, test devices, end stops andsnap-in ground terminal blocks.

Screw clamp technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process.
Mounting, wiring, testing… made easy.
Locking pin 1 allows quick and easy lock up to ten blocks
in position at a time.
Closed jumper location allows great stiffness of the terminal
block, optimal jumper guiding and avoids deflections whiletightening.

1

Lock up to ten blocks in position
at a time

Smart accessories
Flexible test solutions from individual insulated test adapter totest connectors for complete assemblies testing.
–– Direct plug-in into jumpers channels–– 5, 6, 8 mm spacing, mixing various spacing is possible–– 1000 V rating.

Plug-in individual test adapter

Plug-in test connector

Component holder plugs for series or parallel component
mounting (resistors, filters, diodes..).
Can be installed after wiring.
Series plug offers screwless component connection(no soldering).

Series plug associated withdisconnect blocks

Parallel plug to be installed between
2 blocks

Pre-cut poles easy removableby handPredefined shape to identify
connected poles

Smart plug-in jumpers:
Pre-cut poles removable by hand: clean cut.
Insulated up to 1000 V (avoid use of separators).
Predefined shapes in molding to easily identify connected
poles with a pen.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161092S0201

3

Closed jumper location for stiffness

Screw clamp technology - SNK series, terminal blocks
Features and benefits

Optimized logistics
Reduce your accessories inventory by up to 50%
SNK PI-Spring, screw and pluggable ranges share the same
accessories.
Reduced packaging adapted to the usage(20 items packaging for some references).

All end sections and circuit separators fit several types
and sizes of blocks.

3

Stock only one end section for managing your assembly
up to 240 mm²

Shared accessories for SNK PI-Spring, screw and pluggable ranges

Facilitate maintenance operations

Terminals can be individually removed from a terminal
assembly equipped with markers:
TE Connectivity markers become independent after strip
mounting, TE Connectivity markers remain on terminal
in any situation.

Reliable in harsh conditions
Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…

RoHS

CE

EAC

DNV

Rina

1SNK161092S0201

hazlocMaintenance operations facilitated

PAGE 75

SNK series, terminal blocks
Screw clamp technology - Range overview from 4 to 240 mm² – 10 to 500 Kcmil

2

3

Connections

Single deckFeed-throughGroundDisconnect
Fuse

Connections

Single deckFeed-throughGround4

Connections

Single deckFeed-throughGroundDisconnect

3

Double central channels
allows multiconfigurations(jumpering, testing andmeasuring)

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Circuit separator
without spacing loss

Connections

Double deckFeed-throughGroundDisconnect
Fuse
Component holder

2

Connections

Test and measurement
Feed-throughGroundDisconnect

3x 2

Connections

Triple deckFeed-through3

1SNK161089S0201

2x2

Plug
component holder

PAGE 77

SNK series, terminal blocks
Screw clamp technology

Feed-throughGroundSection
12 AWG
10 AWG

4 mm²

10 AWG
6 AWG
4 AWG
3 AWG
0 AWG
2 AWG
50 mm² 0 AWG
70 mm² 00 AWG
95 mm² 0000 AWG
150 mm² 350 Kcmil
240 mm² 500 Kcmil

ZS6
ZS10
ZS16
ZS25

ZS4-PE

ZS6-3S

ZS6-4S

ZS6-PE
ZS10-PE
ZS16-PE
ZS25-PE

ZS6-3S-PE

ZS6-4S-PE

ZS35
ZS35-PE
ZS50-PE
ZS70-PE
ZS95-PE

ZS50
ZS70
ZS95
ZS150
ZS240

Disconnect with blade

Disconnect with plug

Section
4 mm²

10 AWG

ZS4-S

6 mm²
10 mm²10 AWG
6 AWG

ZS6-S
ZS10-SZS4-S-T2ZS4-S-R1

ZS4-S-T2-R1
ZS4-S-T2.3-R1

ZS4-SPZS4-SP-T2

ZS4-SP-R1

ZS4-SP-T2-R1

ZS6-S-4S-T2
ZS10-SPFor 5 x 20 mm fuses

Alignedfor marshalling cabinets application

For 6.3 x 32 mm fuses(¼ x 1¼ in)

Aligned

ZS10-SF

ZS10-S-R2

Section
4 mm²

10 AWG

10 mm²

6 AWG

Clamp -

ZS4-SFZS4-SF-T2

ZS4-SF-R1
ZS4-SF-R3

Channels for jumpering or testing -ZS4-SF-R2
ZS4-SF-R4

Test socket -INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-R2Blown-fuse indicator

ZS4-PE-R2

ZS4-S-R2
ZS10-SF-R1
ZS10-SF-R3

1SNK161066S0201

3

6 mm²
10 mm²16 mm²25 mm²35 mm²

ZS4

Double deckFeed-throughZS4-D2GroundDisconnect
with blade

For 5 x 20 mm
and 5 x 25 mm fuses

ZS4-D1ZS4-D2-S

ZS6-D2

Triple deck

ZS6-D1ZS6-D2-PE

ZS4-D2-S-T2

ZS4-D2-SF1

Component holder

Feed-throughZS4-D-CH-UD ZS4-D-CH-DU

ZS4-T3ZS4-T3-R1

ZS4-D2-SF1-R1
ZS4-D2-SF-R3

ZS6-D1-PE
3

Test & measurement

ZS10-ST

ZS10-ST-T4
ZS10-ST-1

Aligned with ZS10-ST

ZS10-R1

ZS10-PE-R1

For 5 x 20 mm and 5 x 25 mm fuses

ZS4-SF1ZS4-SF1-T2

ZS4-SF1-R1
ZS4-SF1-R3

Feed-throughaligned with ZS4-SF1

ZS4-SF1-R2
ZS4-SF1-R4

ZS4-R1ZS4-S-R3

1SNK161066S0201

Test disconnect with sliding link

PAGE 79

ZS4 screw clamp terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description–– Save space by connecting conductors up to 4 mm² (without insulated ferrule, CB certified) 12 AWG in just
5.2 mm 0.205 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
Description

Color

Feed-through

Grey
Blue
OrangeYellow
GreenRed
Purple
Brown
White
Black

1SNK161001F0014

ZS4

ZS4
ZS4-BLZS4-ORZS4-YLZS4-GNZS4-RDZS4-PRZS4-BRZS4-WHZS4-BK

1SNK505010R0000
1SNK505020R0000
1SNK505030R0000
1SNK505060R0000
1SNK505061R0000
1SNK505062R0000
1SNK505063R0000
1SNK505064R0000
1SNK505065R0000
1SNK505066R0000

48.8 1.92"

56.3 2.22"

5.2 mm 0.205 in spacing

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50
50

8.80
8.80
8.80
8.80
8.80
8.80
8.80
8.80
8.80
8.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 32 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 20 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

26.7 1.05"

Pkg

Part Number

Main technical data

53 2.09"3Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
10.5 mm0.412 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

1

Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
5 Circuit separators 0 mm
0 in
3 mm
0.118 in6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
8 Shield connectors
9 Protecting covers 5.2 mm 0.205 in spacing
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey

Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBS
1SNK900600R0000
PL5
1SNK900618R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
20
10
10
20
10
1960
22
20
10

14.00
2.20
1.30
2.00
2.70
3.50
7.10
36.00
2.80
0.20
5.20
1.70
2.40
5.20
5.20
3.50
1.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS4

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZS4-PEPart Number
1SNK505150R0000

Pkg

Weightqty(1 pce) g

20

12.10

1SNK161001S0201

Accessories

ZS6 screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description
Save space by connecting conductors up to 6 mm² (without insulated ferrule, CB certified) 10 AWG in just
6 mm 0.236 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
Description

Color

Feed-through

Grey
Blue
OrangeYellow
GreenRed
Purple
Brown
White
Black

1SNK161011F0014

ZS6

Type
ZS6
ZS6-BLZS6-ORZS6-YLZS6-GNZS6-RDZS6-PRZS6-BRZS6-WHZS6-BK

1SNK506010R0000
1SNK506020R0000
1SNK506030R0000
1SNK506060R0000
1SNK506061R0000
1SNK506062R0000
1SNK506063R0000
1SNK506064R0000
1SNK506065R0000
1SNK506066R0000

Main technical data

6 mm 0.236 in spacing

48.8 1.92"

56.3 2.22"
26.7 1.05"

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50
50

10.60
10.60
10.60
10.60
10.60
10.60
10.60
10.60
10.60
10.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
41 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 41 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 30 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

53 2.09"

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

3Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
10.5 mm0.412 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

2

CB

RoHS

USR CNRCSAEAC ExATEX

Description
3

5

7

9

11

4

6

8

10

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1
2
3

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
5 Circuit separators 0 mm
0 in
3 mm
0.118 in6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
End module, 5.2 mm 0.205 in
0.031 in8 Spacers
0.8 mm
9 Shield connectors
10 Protecting covers 6 mm 0.236 in spacing
11 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
SHBS
1SNK900600R0000
PL6
1SNK900619R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
20
10
10
20
10
1680
22
20
10

14.00
2.20
1.30
2.10
2.90
3.60
7.40
38.10
2.80
0.20
5.20
1.70
2.40
5.20
0.80
3.50
1.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS6

Green-yellow

Type
ZS6-PEPart Number
1SNK506150R0000

Pkg

Weightqty(1 pce) g

20

13.70

Technical data valid for copper conductors only.

PAGE 81

1SNK161008S0201

1

ZS6-3S screw clamp terminal blocks
Feed-through with 3 connections - 6 mm 0.236 in spacing
Description

6 mm²–– Recommended for energy markets and highly demanding applications requiring that only one conductor beconnected per clamp,–– These blocks offer a high density connecting capacity (up to 3 connections) in a low profile and just 6 mm
0.236 in spacing.

10 AWG

1SNK161075V0014

Ordering details
Description

Color

Type

Feed-through

Grey
Blue
Yellow

Part Number

ZS6-3S
ZS6-3S-BL
ZS6-3S-YL

Main technical data
ZS6-3S57.2 2.25"
35.65 1.40"

6 mm 0.236 in spacing

49.7 1.96"

3Weight(1 pce) g

50
50
50

11.80
11.80
11.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
32 A / 4 mm²
39 A / 6 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

550 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 30 A

1 conductor
per clamp

62 2.44"

1SNK506011R0000
1SNK506021R0000
1SNK506067R0000

Pkg
qty

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

800 V
8000 V
IP20

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque100 kA
600 V

TH 35-7.5,
TH 35-15
10.5 mm0.413 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-3S
1SNK505912R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
20
10
10
1680
22
20
10

14.00
2.50
1.30
2.10
2.90
3.60
7.40
38.10
2.80
0.20
5.20
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS6-3S

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZS6-3S-PE

Part Number
1SNK506151R0000

Pkg

Weightqty(1 pce) g

25

16.20

1SNK161067S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS6-4S screw clamp terminal blocks
Feed-through with 4 connections - 6 mm 0.236 in spacing
Description

6 mm²–– High density wiring (one potential distribution on 4 independent screw clamps) in a very low profile and just
6 mm 0.236 in spacing,–– Recommended for energy markets and highly demanding applications requiring that only one conductor beconnected per clamp.

10 AWG

1SNK161078V0014

Ordering details
Description

Color

Type

Feed-through

Grey
Blue
Yellow

Part Number

ZS6-4S
ZS6-4S-BL
ZS6-4S-YL

1SNK506012R0000
1SNK506022R0000
1SNK506068R0000

Main technical data
ZS6-4S

6 mm 0.236 in spacing

49.7 1.96"

57.2 2.25"
35.65 1.29"

Weight(1 pce) g

50
50
50

15.00
15.00
15.00

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
32 A / 4 mm²
39 A / 6 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

550 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 30 A

1 conductor
per clamp

72.7 2.86"

Pkg
qty

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

800 V
8000 V
IP20

3

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque100 kA
600 V

TH 35-7.5,
TH 35-15
10.5 mm0.413 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
20
10
10
1680
22
20
10

14.00
3.10
1.30
2.10
2.90
3.60
7.40
38.10
2.80
0.20
5.20
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS6-4S

Green-yellow

Type
ZS6-4S-PE

Part Number
1SNK506152R0000

Pkg

Weightqty(1 pce) g

25

19.40

Technical data valid for copper conductors only.

PAGE 83

1SNK161068S0201

1

ZS10 screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Save space by connecting conductors up to 10 mm² (without insulated ferrule, CB certified) 6 AWG in just
8 mm 0.315 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
Description

Color

Feed-through

Grey
Blue
OrangeYellow
GreenRed
Purple
Brown
White
Black

1SNK161008F0014

ZS10

ZS10
ZS10-BL
ZS10-ORZS10-YL
ZS10-GN
ZS10-RD
ZS10-PR
ZS10-BR
ZS10-WH
ZS10-BK

48.8 1.92"

56.3 2.22"

8 mm 0.315 in spacing

1SNK508010R0000
1SNK508020R0000
1SNK508030R0000
1SNK508060R0000
1SNK508061R0000
1SNK508062R0000
1SNK508063R0000
1SNK508064R0000
1SNK508065R0000
1SNK508066R0000

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50
50

14.10
14.10
14.10
14.10
14.10
14.10
14.10
14.10
14.10
14.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
57 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 57 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 42 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

26.7 1.05"

Pkg

Part Number

Main technical data
53 2.09"3Type

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Flat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
42 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
12 mm
0.472 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

1

Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

10 mm
0.394 in0.087 in
2.2 mm57 A (IEC)2 poles
57 A (IEC)3 poles
4 poles
57 A (IEC)57 A (IEC)
5 poles
10 poles
57 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
0 in
5 Circuit separators 0 mm
0.118 in
3 mm
6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
0.110 in8 Spacers
2.8 mm
9 Protecting covers 8 mm 0.315 in spacing
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
PL8
1SNK900620R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
40
20
10
20
20
20
20
10
10
10
10
1680
22
20
10

14.00
2.20
2.70
4.10
5.60
7.00
14.20
2.80
0.20
5.20
1.70
2.40
5.20
5.20
1.40
2.60
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS10

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZS10-PEPart Number
1SNK508150R0000

Pkg

Weightqty(1 pce) g

20

22.50

1SNK161004S0201

Accessories

ZS16 screw clamp terminal blocks
Feed-through - 10 mm 0.394 in spacing
16 mm²
4 AWG

Description–– Save space by connecting conductors up to 16 mm² (without insulated ferrule, CB certified) 4 AWG in just
10 mm 0.394 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
1SNK161006F0014

Description

Color

Feed-through

Grey
Blue
Orange29.8 1.17"

10 mm 0.394 in spacing

50.3 1.98"

57.8 2.28"

56.1 2.21"

Pkg

Part Number

ZS16
ZS16-BL
ZS16-OR1SNK510010R0000
1SNK510020R0000
1SNK510030R0000

Main technical data

Weightqty(1 pce) g

25
25
25

20.20
20.20
20.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 10 mm²
A6-B6
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
76 A / 16 mm²
1920 A

24 ... 4 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 76 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 67 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS16

Type

24 ... 4 AWG
24 ... 8 AWG
20 ... 10 AWG

Flat screwdriver

Tool

3

Ø 5.5 mm
Ø 0.217 in

20 ... 10 AWG
67 A / 4 AWG

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
13.5 mm0.531 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
Description

2
1
2
3

3

4

5

6

4
5
6

7

8

7
8

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
76 A (IEC)3 poles
76 A (IEC)76 A (IEC)4 poles
5 poles
76 A (IEC)76 A (IEC)
10 polesCross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 inProtecting covers 10 mm 0.394 in spacing
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB10-2
1SNK910302R0000
JB10-3
1SNK910303R0000
JB10-4
1SNK910304R0000
JB10-5
1SNK910305R0000
JB10-10
1SNK910310R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
PL10
1SNK900621R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
40
30
20
10
20
20
20
20
10
1680
22
20
10

14.00
2.20
4.60
7.10
9.40
12.00
24.00
2.80
0.20
5.20
1.70
2.40
3.10
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS16

Green-yellow

Type
ZS16-PEPart Number
1SNK510150R0000

Pkg

Weightqty(1 pce) g

20

32.00

Technical data valid for copper conductors only.

PAGE 85

1SNK161017S0201

1

ZS25 screw clamp terminal blocks
Feed-through - 12 mm 0.472 in spacing
25 mm²
3 AWG

Description–– Save space by connecting conductors up to 25 mm² (without insulated ferrule, CB certified) 3 AWG in just
12 mm 0.472 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
1SNK161081V0014

Description

57.8 2.28"
29.8 1.17"

12 mm 0.472 in spacing

50.3 1.98"

56.1 2.21"

Type

Feed-through

Grey
Blue
Yellow

Part Number

ZS25
ZS25-BL
ZS25-YL

1SNK512010R0000
1SNK512020R0000
1SNK512060R0000

Main technical data

Pkg

Weightqty(1 pce) g

25
25
25

21.40
21.40
21.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 25 mm²
0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
A6-B6
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
76 A / 16 mm²
101 A / 25 mm²
1920 A

24 ... 3 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 69 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 100 A

1 conductor
per clamp

ZS25

3

Color

24 ... 4 AWG
24 ... 8 AWG
20 ... 10 AWG

1000 V
8000 V
IP20

Flat screwdriverToolØ 5.5 mm
Ø 0.217 in

20 ... 10 AWG
100 A / 3 AWG

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque100 kA
600 V

TH 35-7.5,
TH 35-15
13.5 mm0.531 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4
4
5

5

7

6

8

6
7
8

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
76 A (IEC)3 poles
76 A (IEC)76 A (IEC)
5 poles
Cross spacing jumpers 3 poles
32 A (IEC)
0 in
Circuit separators 0 mm
0.118 in3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 inProtecting covers 10 mm 0.394 in spacing
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB12-2
1SNK912302R0000
JB12-3
1SNK912303R0000
JB12-5
1SNK912305R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
PL10
1SNK900621R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
20
10
20
20
20
20
10
1680
22
20
10

14.00
2.20
4.90
7.60
12.90
2.80
0.20
5.20
1.70
2.40
3.10
0.27
10.00
14.00
0.20

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS25

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZS25-PEPart Number
1SNK512150R0000

Pkg

Weightqty(1 pce) g

20

38.00

1SNK161078S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS35 screw clamp terminal blocks
Feed-through - 16 mm 0.630 in spacing
Description

35 mm²

Closed terminal block:–– No end section needed,–– Optimized rigidity,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

0 AWG

1SNK161004F0014

Ordering details
Description
Feed-through

Color
Closed block

Type

Grey
Blue
Orange

ZS35
ZS35-BL
ZS35-OR1SNK516010R0000
1SNK516020R0000
1SNK516030R0000

Main technical data
ZS35

16 mm 0.630 in spacing

55.8 2.19"

63.3 2.49"
34 1.34"

Weightqty(1 pce) g

20
20
20

53.40
53.40
53.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

6 ... 35 mm²
6 ... 35 mm²
4 ... 35 mm²
4 … 35 mm²
A9-B9
6 ... 16 mm²
6 ... 16 mm²
4 … 10 mm²
125 A / 35 mm²4200 A

10 ... 0 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 125 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 150 A UL 60079-7 - Class I, Zone 1, AEx e II

1 conductor
per clamp

59 2.32"

Pkg

Part Number

10 ... 2 AWG
10 ... 2 AWG
10 ... 6 AWG

Tool

Flat screwdriverØ 6.5 mm
Ø 0.256 in

Torque2.9 Nm ± 0.1
25.7 lb.in ± 0.885

12 ... 8 AWG
150 A / 0 AWG
100 kA
600 V

1000 V
8000 VIP10

TH 35-7.5,
TH 35-15
17 mm
0.669 in

3

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
Description

2
1
2

3

5

4
3
4
5

Color

10 mm
0.394 in
2 poles
125 A (IEC)3 poles
125 A (IEC)125 A (IEC)4 poles
5 poles
125 A (IEC)125 A (IEC)
10 polesCircuit separators 3 mm
0.118 inProtecting covers 16 mm 0.630 in spacing
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Dark grey
OrangeDark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB16-2
1SNK916302R0000
JB16-3
1SNK916303R0000
JB16-4
1SNK916304R0000
JB16-5
1SNK916305R0000
JB16-10
1SNK916310R0000
CS-R1
1SNK900103R0000
PL16
1SNK900622R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
10
10
10
10
10
20
10
1680
22
20
10

24.00
10.00
16.00
22.00
28.00
56.60
5.20
4.60
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS35

Green-yellow

Type
ZS35-PEPart Number
1SNK516150R0000

Pkg

Weightqty(1 pce) g

20

81.80

Technical data valid for copper conductors only.

PAGE 87

1SNK161019S0201

1

ZS50 screw clamp terminal blocks
Feed-through - 16 mm 0.630 in spacing
50 mm²0 AWG

Description
Combine high performance with compact dimensions:–– Connect conductors up to 50 mm² (CB certified) 0 AWG in just 16 mm 0.630 in spacing,–– Perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC and 1000 V UL,–– Closed terminal block: no end section needed, optmized rigidity.

1SNK161084V0014

Ordering details
Description
Feed-through

Color

Type

Closed block

Grey
Blue
YellowRed
Black

Part Number

ZS50
ZS50-BL
ZS50-YL
ZS50-RD
ZS50-BK

1SNK516011R0000
1SNK516021R0000
1SNK516060R0000
1SNK516063R0000
1SNK516064R0000

Main technical data
Connecting capacity

IEC

UL - CSARail

1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
Dia.11
1 … 25 mm²
1 … 25 mm²
1 … 16 mm²
150 A / 50 mm²6000 A

18 … 0 AWG

Wire stripping
length16 mm 0.630 in spacing

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection
Increased safety Ex e

880 V 150 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC

1 conductor
per clamp

69.3 2.73"
31.9 1.25"

61.8 2.43"

63.6 2.50"

Weight(1 pce) g

20
20
20
20
20

52.90
52.90
52.90
52.90
52.90

Mounting instructions

ZS50

3

Pkg
qty

18 … 0 AWG
18 … 0 AWG
18 … 4 AWG

1000 V
8000 V
IP10

Flat screwdriverToolØ 6.5 mm
Ø 0.256 in

18 … 4 AWG
140 A / 0 AWG

3 Nm ± 0.50
26.6 lb.in ± 4.43

Torque100 kA
1000 VTH 35-7.5,
TH 35-15
17 mm
0.669 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2

End stops
Jumper bars

3

Terminal block
markers

3

Color
10 mm
0.394 in
2 poles
125 A (IEC)3 poles
125 A (IEC)125 A (IEC)4 poles
5 poles
125 A (IEC)125 A (IEC)
10 polesBlank marker
Blank card

Dark grey
OrangeWhite

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB16-2
1SNK916302R0000
JB16-3
1SNK916303R0000
JB16-4
1SNK916304R0000
JB16-5
1SNK916305R0000
JB16-10
1SNK916310R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
10
10
10
10
10
1680
22
20
10

24.00
10.00
16.00
22.00
28.00
56.60
0.27
10.00
14.00
0.20

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS50

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZS50-PEPart Number
1SNK516151R0000

Pkg

Weightqty(1 pce) g

20

83.00

1SNK161069S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS70 screw clamp terminal blocks
Feed-through - 22 mm 0.866 in spacing
70 mm²00 AWG

Description
Closed terminal block:–– No end section needed,–– Optimized rigidity,–– Perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC and 1000 V UL.

1SNK161044F0014

Ordering details
Description
Feed-through

Color

Type

Closed block

Grey
Blue
Yellow

ZS70
ZS70-BL
ZS70-YL

1SNK522010R0000
1SNK522020R0000
1SNK522060R0000

Main technical data
ZS70

75 2.95"

82.5 3.25"
39.5 1.56"

22 mm 0.866 in spacing

Weightqty(1 pce) g

10
10
10

158.10158.10158.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

16 ... 95 mm²
16 ... 70 mm²
16 ... 50 mm²
16 ... 50 mm²
B11
16 ... 35 mm²
16 ... 35 mm²
16 mm²
192 A / 70 mm²8400 A

4 ... 00 AWG

Wire stripping
length4 ... 2 AWG

Tool

Allen keyØ 6 mmØ 0.236 in

Torque6.5 Nm ± 0.5
57.5 lb.in ± 4.43

Increased safety Ex e

693 V 192 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 159 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp
78.4 3.09"

Pkg

Part Number

6 AWG
159 A / 00 AWG
100 kA
1000 V

1000 V
8000 VIP10

TH 35-7.5,
TH 35-15
25 mm
0.984 in

3

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
Description

2
1
2

End stops
Jumper bars

3

Terminal block
markers

3

Color
10 mm
0.394 in
2 poles
192 A (IEC)
192 A (IEC)3 poles
5 poles
192 A (IEC)
192 A (IEC)
10 polesBlank marker
Blank card

Dark grey

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB22-2
1SNK922302R0000
JB22-3
1SNK922303R0000
JB22-5
1SNK922305R0000
JB22-10
1SNK922310R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
5
5
5
5
1680
22
20
10

24.00
27.00
43.30
76.10
157.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS70

Green-yellow

Type
ZS70-PEPart Number
1SNK522150R0000

Pkg

Weightqty(1 pce) g

10222.00Technical data valid for copper conductors only.

PAGE 89

1SNK161021S0201

1

ZS95 screw clamp terminal blocks
Feed-through - 26 mm 1.024 in spacing
95 mm²0000 AWG

Description
Closed terminal block:–– No end section needed,–– Optimized rigidity,–– Perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC and 1000 V UL.

1SNK161025F0014

Ordering details
Description
Feed-through

Color

Type

Closed block

Grey
Blue
Yellow

ZS95
ZS95-BL
ZS95-YL

1SNK526010R0000
1SNK526020R0000
1SNK526060R0000

Main technical data
ZS95

79.5 3.13"

87 3.43"
46 1.81"

26 mm 1.024 in spacing

Weightqty(1 pce) g

10
10
10

215.10215.10215.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

35 ... 120 mm²
35 ... 95 mm²
35 ... 50 mm²
35 ... 50 mm²
B12
25 ... 35 mm²
25 ... 35 mm²
16 mm²232 A / 95 mm²11400 A

2 ... 0000 AWG

Wire stripping
length4 ... 2 AWG

Tool

Increased safety Ex e

693 V 232 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 230 A UL 60079-7 - Class I, Zone 1, AEx e II

1 conductor
per clamp

87 3.43"

3

Pkg

Part Number

Allen keyØ 6 mmØ 0.236 in

6 AWG
230 A / 0000 AWG

9.25 Nm ± 0.25
81.7 lb.in ± 2.21

Torque100 kA
1000 V

1000 V
8000 VIP10

TH 35-7.5,
TH 35-15
26 mm
1.024 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

Description

2
1
2

End stops
Jumper bars

3

Terminal block
markers

3

Color
10 mm
0.394 in
2 poles
232 A (IEC)232 A (IEC)3 poles
5 poles
232 A (IEC)232 A (IEC)
10 polesBlank marker
Blank card

Dark grey

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB26-2
1SNK926302R0000
JB26-3
1SNK926303R0000
JB26-5
1SNK926305R0000
JB26-10
1SNK926310R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
5
5
5
5
1680
22
20
10

24.00
41.20
65.70
115.70241.50
0.27
10.00
14.00
0.20

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS95

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSGreen-yellow

Type
ZS95-PEPart Number
1SNK526150R0000

Pkg

Weightqty(1 pce) g

10278.00

1SNK161023S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS150 screw clamp terminal blocks
Feed-through - 31 mm 1.220 in spacing
150 mm²
350 Kcmil

Description–– Perfectly adapted to solar applications : 1500V DC (1000V AC) IEC and 1000V UL,–– Closed terminal block: no end section needed, optimized rigidity,–– Ease your voltage monitoring or distribution with the 2 built-in derivations,–– Use of jumper bars requires the user to cut-out the partition.

1SNK161150V0014

Ordering details
Description

Color

Type

Part Number

Closed block with 2 x 10 mm²
derivations.

Feed-through

Grey
Blue
Yellow

ZS150
ZS150-BL
ZS150-YL

1SNK531010R0000
1SNK531020R0000
1SNK531060R0000

Main technical data
ZS150

Mounting instructions

114.5 4.50"

110 4.33"

36.5 1.43"

31 mm 1.220 in spacing

UL

Rail

Connecting capacity

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rigid: Solid/Stranded
Derivation with
1 conductor per Flexible without ferrule
clamp
Gauge
Rated current / Rated cross section
Main circuit Copper
Aluminium
Derivation
Rated short-time withstand current (1s)
V AC
Rated voltage
V DC
Impulse withstand voltage
Protection

35 ... 185 mm² 2 … 350 Kcmil 2 … 350 Kcmil Main circuit
50 ... 150 mm²
Wire stripping
lengthB14
Tool
0.5 ... 16 mm² 20 ... 8 AWG 20 ... 8 AWG
0.5 ... 10 mm² 20 ... 8 Kcmil 20 ... 8 Kcmil
B6
TorqueIncreased safety Ex e1000 V 309 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC

Main circuit with
1 conductor per
clamp
119.4 4.70"

Pkg Weight(1 pce) g
5318.005318.005318.00qty

CSA

309 A / 150 mm² 310 A / 350 Kcmil 310 A / 350 Kcmil Derivation
Wire stripping
57 A / 10 mm² 50 A / 8 AWG 50 A / 8 AWG
length18000 A
Tool
1000 V
1000 V
1000 V
1500
12000 VTorqueIP10NEMA 1

TH 35-7.5,
TH 35-15
40 mm
1.575 inAllen keyØ 8 mmØ 0.315 in
20 Nm
177 lb.in

3

12 mm
0.47 inFlat screwdriverØ 4 mmØ 0.157 in
1.2 Nm ... 1.4 Nm
10.6 lb.in ... 12.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

Accessories

3

Description

2

4

Color

1
2

End stops
Jumper bars

10 mm
2 poles
3 poles

3
4

Protecting covers
Terminal block
Blank card
markers
Blank marker
Blank card

0.394 in
309 A (IEC)309 A (IEC)

Universal wire markers holder

Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
BJMI31.2
1SNA206053R0700
BJMI31.3
1SNA206054R0000
CPBP1
1SNA399788R1600
RC1010
1SNA238000R1600
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1
1
20
10
1680
22
20
10

24.00
120.00190.00
0.40
1.30
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161093S0201

1

Technical data valid for copper conductors only.

PAGE 91

ZS240 screw clamp terminal blocks
Feed-through - 36 mm 1.417 in spacing
240 mm²
500 Kcmil

Description–– Perfectly adapted to solar applications : 1500V DC (1000V AC) IEC and 1000V UL,–– UL Certified for aluminum cables use - Closed terminal block: no end section needed, optimized rigidity,–– Ease your voltage monitoring or distribution with the 2 built-in derivations,–– Use of jumper bars requires the user to cut-out the partition.

1SNK161153V0014

Ordering details
Description

Color

Type

Part Number

Closed block with 2 x 10 mm²
derivations.

Feed-through

Grey
Blue
Yellow

ZS240
ZS240-BL
ZS240-YL

1SNK536010R0000
1SNK536020R0000
1SNK536060R0000

Main technical data
ZS240

Mounting instructions

124.5 4.90"

110 4.33"

36.5 1.43"

36 mm 1.417 in spacing

UL

Rail

Connecting capacity

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rigid: Solid/Stranded
Derivation with
1 conductor per Flexible without ferrule
clamp
Gauge
Rated current / Rated cross section
Main circuit Copper
Aluminium
Derivation
Rated short-time withstand current (1s)
V AC
Rated voltage
V DC
Impulse withstand voltage
Protection

50 ... 300 mm² 0 … 500 Kcmil 0 … 500 Kcmil Main circuit
50 ... 240 mm²
Wire stripping
lengthB14
Tool
0.5 ... 16 mm² 20 ... 8 AWG 20 ... 8 AWG
0.5 ... 10 mm² 20 ... 8 Kcmil 20 ... 8 Kcmil
B6
TorqueIncreased safety Ex e1000 V 415 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC

Main circuit with
1 conductor per
clamp

119.4 4.70"

3

Pkg Weight(1 pce) g
5366.005366.005366.00qty

CSA

415 A / 240 mm² 380 A / 500 Kcmil 380 A / 500 Kcmil Derivation
271 / 500 Kcmil 271 / 500 Kcmil
Wire stripping
57 A / 10 mm² 50 A / 8 AWG 50 A / 8 AWG
length28800 A
Tool
1000 V
1000 V
1000 V
1500
12000 VTorqueIP10NEMA 1

TH 35-7.5,
TH 35-15
38 mm
1.496 inAllen keyØ 8 mmØ 0.315 in
25 Nm
221.3 lb.in
12 mm
0.47 inFlat screwdriverØ 4 mmØ 0.157 in
1.2 Nm ... 1.4 Nm
10.6 lb.in ... 12.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

Accessories
1

3

Description

2

4

Color

1
2

End stops
Jumper bars

10 mm
2 poles
3 poles

3
4

Protecting covers
Terminal block
Blank card
markers
Blank marker
Blank card

0.394 in
415 A (IEC)415 A (IEC)

Universal wire markers holder

Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
BJMI36.2
1SNA206126R2500
BJMI36.3
1SNA206223R0600
CPBP2
1SNA399787R0500
RC1010
1SNA238000R1600
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1
1
20
10
1680
22
20
10

24.00
170.00260.00
1.30
1.30
0.27
10.00
14.00
0.20

1SNK161094S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-PE screw clamp terminal blocks
Ground - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.

1SNK161018F0014

Ordering details
Description

Color
Screwless rail connection

Ground1 conductor
per clamp

Pkg

Part Number

Green-yellow

ZS4-PE

1SNK505150R0000

IEC

UL - CSARail

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

0.2 ... 4 mm²
24 ... 12 AWG
0.22 ... 4 mm²0.22 ... 4 mm²
24 ... 12 AWG
0.22 ... 2.5 mm² 24 ... 14 AWG
A3-B3

56.3 2.22"

48.8 1.92"(1 pce) g

20

12.10

TH 35-7.5,
TH 35-15
10.5 mm0.412 in

Wire stripping
lengthFlat screwdriverTool

59.5 2.26"

26.7 1.05"

Weightqty

Mounting instructions

Connecting capacity

ZS4-PETypeØ 3.5 mm
Ø 0.138 in

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

3

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

14.00
2.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161002S0201

1

Technical data valid for copper conductors only.

PAGE 93

ZS6-PE screw clamp terminal blocks
Ground - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.

1SNK161017F0014

Ordering details
Description

Color
Screwless rail connection

Ground1 conductor
per clamp

Green-yellow

ZS6-PE

1SNK506150R0000

IEC

UL - CSA

Rail

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
length56.3 2.22"

48.8 1.92"(1 pce) g

20

13.70

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriver

Tool

26.7 1.05"

Weightqty

Mounting instructions

59.5 2.26"

3

Pkg

Part Number

Main technical data
Connecting capacity

ZS6-PETypeØ 4 mmØ 0.157 in

Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
11.00
0.20

1SNK161015S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS6-3S-PE screw clamp terminal blocks
Ground with 3 connections - 6 mm 0.236 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– rail contact non operator dependent, secured snap on or off the rail,–– Same profile as ZS6-3S for aligned marking and identical end section.

10 AWG

1SNK161090V0014

Ordering details
Description

Color
Screwless rail connection

GroundPart Number

Green-yellow

ZS6-3S-PE

1SNK506151R0000

IEC

UL - CSA

Rail

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

57.2 2.25"

49.7 1.96"

Weight(1 pce) g

25

16.20

Rated cross section
Maximum cross section
Rated short-time withstand current (1s)Maximum short-time withstand current (1s)

4 mm²
6 mm²
480 A
480 A

10 AWG

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

Ø 4 mmØ 0.157 in

3

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque636 A

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriver

Tool

68.5 2.69"

35.65 1.40"

Pkg
qty

Mounting instructions

Connecting capacity

ZS6-3S-PE

Type

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-3S
1SNK505912R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.50
5.20
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161080S0201

1

Technical data valid for copper conductors only.

PAGE 95

ZS6-4S-PE screw clamp terminal blocks
Ground with 4 connections - 6 mm 0.236 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– rail contact non operator dependent, secured snap on or off the rail,–– Same profile as ZS6-4S for aligned marking and identical end section.

10 AWG

1SNK161091V0014

Ordering details
Description

Color
Screwless rail connection

GroundPart Number

Green-yellow

ZS6-4S-PE

IEC

UL - CSA

Rail

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

79.2 3.12"

1SNK506152R0000

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

6 mm 0.236 in spacing

49.7 1.96"

57.2 2.3"
35.7 1.4"

Weight(1 pce) g

25

19.40

Rated cross section
Maximum cross section
Rated short-time withstand current (1s)Maximum short-time withstand current (1s)

4 mm²
6 mm²
480 A
480 A

10 AWG

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

Ø 4 mmØ 0.157 in

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque636 A

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriver

Tool

3

Pkg
qty

Mounting instructions

Connecting capacity
ZS6-4S-PE

Type

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
3.10
5.20
0.27
10.00
11.00
0.20

1SNK161081S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS10-PE screw clamp terminal blocks
Ground - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.

1SNK161016F0014

Ordering details
Description

Color
Screwless rail connection

Ground1 conductor
per clamp

Pkg

Part Number

Green-yellow

ZS10-PE

1SNK508150R0000

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²
A5-B5

24 ... 6 AWG

Wire stripping
lengthMain technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 8 AWG
24 ... 8 AWG

56.3 2.22"(1 pce) g

20

22.50

TH 35-7.5,
TH 35-15
12 mm
0.472 inFlat screwdriverTool

59.5 2.26"

26.7 1.05"

Weightqty

Mounting instructions

Connecting capacity

ZS10-PEType

Ø 4 mmØ 0.157 in

Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

3

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161016S0201

1

Technical data valid for copper conductors only.

PAGE 97

ZS16-PE screw clamp terminal blocks
Ground - 10 mm 0.394 in spacing
16 mm²

1SNK161019F0014

4 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail,–– PE.N function available by combining ZS16-PE with ZS16-BL and 2 poles jumper bar JB10-2.

Ordering details
Description

Color
Screwless rail connection

GroundType

Green-yellow

ZS16-PE

1SNK510150R0000

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 10 mm²
A6-B6

24 ... 4 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

60.6 2.39"

27.9 1.10"

10 mm 0.394 in spacing(1 pce) g

20

32.00

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 4 AWG
24 ... 8 AWG

TH 35-7.5,
TH 35-15
13.5 mm0.531 inFlat screwdriverTool

56.3 2.22"

3Weightqty

Mounting instructions

Connecting capacity
ZS16-PE

Pkg

Part Number

Ø 5.5 mm
Ø 0.217 in

Rated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG
2544 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

1SNK161018S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS25-PE screw clamp terminal blocks
Ground - 12 mm 0.472 in spacing
Description

25 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– rail contact non operator dependent, secured snap on or off the rail,–– Same profile as ZS25 for aligned marking and identical end section.

3 AWG

Ordering details
1SNK161092V0014

Description

Color
Screwless rail connection

GroundTypePart Number

Green-yellow

ZS25-PE

1SNK512150R0000

IEC

UL - CSA

Rail

0.5 ... 25 mm²
0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
A6-B6

24 ... 3 AWG

Wire stripping
lengthMain technical data

ZS25-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 4 AWG
24 ... 8 AWG

57.8 2.28"

50.3 1.98"

20

38.00

Ø 5.5 mm
Ø 0.217 in

Rated cross section
Maximum cross section
Rated short-time withstand current (1s)Maximum short-time withstand current (1s)

16 mm²25 mm²1920 A
3000 A

3 AWG

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

3

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque3204 ATH 35-7.5,
TH 35-15
13.5 mm0.531 inFlat screwdriverTool
63.6 2.5"

29.8 1.17"

Weight(1 pce) g

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

12 mm 0.472 in spacing

CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161082S0201

1

Technical data valid for copper conductors only.

PAGE 99

ZS35-PE screw clamp terminal blocks
Ground - 16 mm 0.630 in spacing
35 mm²
2 AWG

Description
Reliable electrical and mechanical contact with the rail that exceeds the requirements of IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

1SNK161005F0014

GroundRigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Green-yellow

ZS35-PEIEC

UL - CSA

Rail

6 ... 35 mm²
6 ... 35 mm²
4 ... 35 mm²
4 … 35 mm²A910 ... 2 AWG

Wire stripping
length35 mm²4200 A

Rated cross section
Rated short-time withstand current (1s)63.3 2.49"

Pkg

Part Number
1SNK516150R0000

Weightqty(1 pce) g

20

81.80

Mounting instructions

Connecting capacity

ZS35-PE

59 2.32"

Type

Main technical data
1 conductor
per clamp

3

Color

10 ... 2 AWG
10 ... 2 AWG

TH 35-7.5,
TH 35-15
17 mm
0.669 inFlat screwdriver

Tool
Screw clamp

Ø 6.5 mm
Ø 0.256 in
Ø 5.5
Ø 0.217

Rail connection
screw

2 AWG
4032 ATorqueScrew clamp

2.65 Nm ± 0.15
23.4 lb.in ± 1.33
1.6 Nm ± 0.15 Nm
14.2 lb.in ± 1.33 lb.in

Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

34 1.34"

16 mm 0.630 in spacing

Accessories
1

Description

2
1
2
3

3

End stops
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
1680
22
20
10

24.00
5.20
0.27
10.00
14.00
0.20

1SNK161020S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS35-PEN screw clamp terminal blocks
Ground + neutral - 32 mm 1.260 in spacing
Description

35 mm²

N

Simplify your PE.N connection with ZS35-PE block connected to ZS35-BL through a pre-mounted jumper.

Ordering details
Description

Color

1SNK161063F0014

Ground + neutral

ZS35-PENIEC

UL - CSA

1 conductor
per clamp

Part Number
1SNK516170R0000

Pkg

Weightqty(1 pce) g

10

236.00

Mounting instructions

Connecting capacity
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

6 ... 35 mm²
6 ... 35 mm²
6 ... 35 mm²
6 ... 35 mm²A910 ... 2 AWG

Wire stripping
lengthRail connection
screw
TorqueScrew clamp

IP10

Protection

Rail

Tool
Screw clamp

35 mm²4200 A

Rated cross section
Rated short-time withstand current (1s)63.3 2.49"

Green-yellow

Main technical data

ZS35-PEN

60.3 2.37"

Type

NEMA 1

Rail connectionscrew

TH 35-7.5,
TH 35-15
17 mm
0.669 inFlat screwdriverØ 6.5 mm
Ø 0.256 in
Ø 5.5
Ø 0.21732.65 Nm ± 0.15
23.5 lb.in ± 1.33
1.6 Nm ± 0.15 Nm
14.2 lb.in ± 1.33 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

EAC

34 1.34"

32 mm 1.260 in spacing

Accessories
Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161047S0201

1

Technical data valid for copper conductors only.

PAGE 101

ZS50-PE screw clamp terminal blocks
Ground - 16 mm 0.630 in spacing
50 mm²0 AWG

Description–– Reliable electrical and mechanical contact with the rail that exceeds the requirements of the IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

1SNK161093V0014

GroundRigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Green-yellow

ZS50-PEIEC

UL - CSARail

1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
Dia.11

18 … 0 AWG

Wire stripping
length50 mm²6000 A

Rated cross section
Rated short-time withstand current (1s)69.3 2.73"

Part Number
1SNK516151R0000

Pkg

Weightqty(1 pce) g

20

83.00

Mounting instructions

Connecting capacity

ZS50-PE

63.6 2.50"

Type

Main technical data
1 conductor
per clamp

3

Color

18 … 0 AWG
18 … 0 AWG

Tool
Screw clamp
Rail connection
screw

0 AWG
6420 ATorqueScrew clamp
Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

TH 35-7.5,
TH 35-15
17 mm
0.669 inFlat screwdriverØ 6.5 mm
Ø 0.256 in
Ø 6.5
Ø 0.256

3 Nm ± 0.50
26.6 lb.in ± 4.43
3 Nm ± 0.25 Nm
26.553 lb.in ± 2.21 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

31.9 1.25"

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

16 mm 0.630 in spacing

Accessories
1

Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

1SNK161070S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS70-PE screw clamp terminal blocks
Ground - 22 mm 0.866 in spacing
70 mm²00 AWG

Description
Reliable electrical and mechanical contact with the rail that exceeds the requirements of IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

Ground1SNK161045F0014

Color

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge(1 pce) g

10222.00

Green-yellow

ZS70-PEIEC

UL - CSARail

TH 35-15

16 ... 95 mm²
16 ... 70 mm²
16 ... 50 mm²
16 ... 50 mm²
B11

4 ... 00 AWG

Wire stripping
length25 mm
0.984 in

70 mm²8400 A

Rated cross section
Rated short-time withstand current (1s)82.6 3.25"

1SNK522150R0000

Weightqty

Mounting instructions

Connecting capacity

ZS70-PE

Pkg

Part Number

Main technical data
1 conductor
per clamp

74 2.91"

Type

Allen key

Tool
Screw clamp

Ø 6 mmØ 0.236 in
Ø 4
Ø 0.158

Rail connectionscrew

00 AWG
8088 A

3

TorqueScrew clamp

6.5 Nm ± 0.5
57.5 lb.in ± 4.43
1.9 Nm ± 0.1 Nm
16.82 lb.in ± 0.885 lb.in

Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

39.5 1.56"

22 mm 0.866 in spacing

Accessories
Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161022S0201

1

Technical data valid for copper conductors only.

PAGE 103

ZS95-PE screw clamp terminal blocks
Ground - 26 mm 1.024 in spacing
95 mm²0000 AWG

Description
Reliable electrical and mechanical contact with the rail that exceeds the requirements of IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

1SNK161024F0014

GroundRigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

1SNK526150R0000

Weightqty(1 pce) g

10278.00

Green-yellow

ZS95-PEIEC

UL - CSARail

TH 35-15

35 ... 120 mm²
35 ... 95 mm²
35 ... 50 mm²
35 ... 50 mm²B12

2 ... 0000 AWG

Wire stripping
length26 mm
1.024 in

95 mm²11400 A

Rated cross section
Rated short-time withstand current (1s)

87 3.43"

Pkg

Part Number

Mounting instructions

Connecting capacity

ZS95-PE

87 3.43"

Type

Main technical data
1 conductor
per clamp

3

Color

Allen key

Tool
Screw clamp

0000 AWG
12840 A

Ø 6 mmØ 0.236 in
Ø 4
Ø 0.158

Rail connection
screw
TorqueScrew clamp

9.25 Nm ± 0.25
81.7 lb.in ± 2.2
1.9 Nm ± 0.1 Nm
16.82 lb.in ± 0.885 lb.in

Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

46 1.81"

26 mm 1.024 in spacing

Accessories
1

Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

1SNK161024S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-S screw clamp terminal blocks
Disconnect with blade - 5.2 mm 0.205 in spacing
4 mm²
10 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

Ordering details

1SNK161002F0014

Description

Color
Profile aligned with ZS4Disconnect

Grey
Blue
Orange26.7 1.05"

5.2 mm 0.205 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"

53 2.09"

Pkg

Part Number

ZS4-S
ZS4-S-BLZS4-S-OR

1SNK505310R0000
1SNK505320R0000
1SNK505330R0000

Main technical data

Weightqty(1 pce) g

50
50
50

8.60
8.60
8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²
0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
25 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp
ZS4-S

Type

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
25 A / 10 AWG

3

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

Description

2
1
2
3

3

5

4

6

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
0.118 inCircuit separators 3 mm
Shield connectors
Protecting covers 5.2 mm 0.205 in spacing
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey
Dark grey
Transparent
White

Grey

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
CS-R1
1SNK900103R0000
SHBS
1SNK900600R0000
PL5
1SNK900618R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
10
1960
22
20
10

14.00
2.20
1.80
6.00
5.20
3.50
1.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161010S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

PAGE 105

ZS4-S-T screw clamp terminal blocks
Disconnect with blade - with test socket - 5.2 mm 0.205 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets,–– Screwdriver or hand operated disconnect blade,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

10 AWG

Ordering details
1SNK161034F0014

Description
Disconnect

Color
Profile aligned with ZS4, with 2 test
sockets DIA 2 mm 0.079 in

Type

Grey
Blue
OrangeGrey

Profile aligned with ZS4, with 2 test
sockets DIA 2.3 mm 0.091 in

ZS4-S-T2ZS4-S-T2-BL
ZS4-S-T2-OR
ZS4-S-T2.3

Main technical data

Part Number
1SNK505311R0000
1SNK505321R0000
1SNK505331R0000
1SNK505312R0000

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
25 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

59.7 2.35"

60.4 2.37"
26.7 1.05"

5.2 mm 0.205 in spacing

52.9 2.08"
67.2 2.64"

53 2.09"

Weight(1 pce) g

50
50
50
50

8.90
8.90
8.90
8.80

Mounting instructions

Connecting capacity
ZS4-S-T

3

Pkg
qty

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
25 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

3

5

Description

2

4

6

1
2
3
4
5
6
7

Color

End stops
10 mm
0.394 in0.087 inEnd sections
2.2 mm30 A (IEC)
Lateral jumper bars 2 poles
30 A (IEC)
10 polesCircuit separators 3 mm
0.118 inShield connectors
Protecting covers 5.2 mm 0.205 in spacing
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey
Dark grey
Transparent
White

Grey

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
CS-R1
1SNK900103R0000
SHBS
1SNK900600R0000
PL5
1SNK900618R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
10
1960
22
20
10

14.00
2.20
1.80
6.00
5.20
3.50
1.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161042S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-S-R1 screw clamp terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing
Description

4 mm²–– Simplify the alternated distribution thanks to the two jumper channels aligned with ZS4 feed-through terminal blocks,–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver.

10 AWG

Ordering details
1SNK161003F0014

Description

Color
Profile aligned with ZS4-SF

Disconnect

Type

Grey
Blue
OrangeZS4-S-R1
ZS4-S-R1-BL
ZS4-S-R1-OR

1SNK506310R0000
1SNK506320R0000
1SNK506330R0000

Main technical data
ZS4-S-R1

6 mm 0.236 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"
26.7 1.05"

Weightqty(1 pce) g

50
50
50

13.20
13.20
13.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
26 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

70.5 2.78"

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriver

Tool

3

Ø 3.5 mm
Ø 0.138 in

24 ... 16 AWG
26 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
Description

2

3

4

5

6

1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161012S0201

1

Technical data valid for copper conductors only.

PAGE 107

ZS4-S-T-R1 screw clamp terminal blocks
Disconnect with blade - with test socket - 6 mm 0.236 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets,–– Screwdriver or hand operated disconnect blade,–– Simplify the alternated distribution thanks to the two jumper channels aligned with ZS4 feed-through terminal blocks.

1SNK161035F0014

10 AWG

Ordering details
Description

Color
Profile aligned with ZS4-SF, with 2
test sockets DIA 2 mm 0.079 in

Disconnect

Grey
Blue
OrangeGrey

Profile aligned with ZS4-SF, with 2
test sockets DIA 2.3 mm 0.091 in

ZS4-S-T-R1

Type
ZS4-S-T2-R1
ZS4-S-T2-R1-BL
ZS4-S-T2-R1-OR
ZS4-S-T2.3-R1

Main technical data
70.5 2.78"

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"
26.7 1.05"

6 mm 0.236 in spacing

1SNK506311R0000
1SNK506321R0000
1SNK506331R0000
1SNK506312R0000

Weightqty(1 pce) g

50
50
50
50

14.20
14.20
14.20
14.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
26 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

3

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
26 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
Description
1

3

5

Color

Type

Part Number

2
1
2

End stops
Jumper bars

3
4
5

Test connectors
Spacers
Terminal block
markers4

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 polesEnd module, 5.2 mm 0.205 in
0.031 in
0.8 mmBlank marker
Blank card

Dark grey

Universal wire markers holder

Grey

OrangeDark grey
Dark grey
White

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
0.27
10.00
11.00
0.20

1SNK161045S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS6-S screw clamp terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver,–– Same profile as ZS6 feed-through terminal block for aligned marking and identical end section use.

Ordering details

1SNK161056F0014

Description

Color
Profile aligned with ZS6Disconnect

Grey
Blue

26.7 1.05"

6 mm 0.236 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"

53 2.09"

Part Number

ZS6-S
ZS6-S-BL

1SNK506315R0000
1SNK506322R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

8.60
8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 6 mm²0.22 ... 6 mm²0.22 ... 6 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²
25 A / 4 mm²
30 A / 6 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

500 V
6000 V
IP20

1 conductor
per clamp

ZS6-S

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
25 A / 10 AWG

30.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque300 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories

3

5

Description

2

4

6

1
2
3
4
5
6

End stops
End sections
Circuit separators
Shield connectors
Protecting covers
Terminal block
markers

Color
10 mm
2.2 mm3 mm

0.394 in0.087 in
0.118 in

Dark grey

6 mm 0.236 in spacing
Blank marker
Blank card

Transparent

Universal wire markers holder

Dark grey
Dark grey

White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
SHBS
1SNK900600R0000
PL6
1SNK900619R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
10
1680
22
20
10

14.00
2.20
5.20
3.50
1.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161046S0201

1

Technical data valid for copper conductors only.

PAGE 109

ZS6-S-4S-T screw clamp terminal blocks
Disconnect with blade - with test socket screws - 6 mm 0.236 in spacing
Description

6 mm²–– Recommended for energy markets and highly demanding applications requiring that only one conductor beconnected per clamp,–– Ease your disconnect and test operations with the two built-in test socket screws,–– Simplify the alternated distribution thanks to the jumper channel.

1SNK161094V0014

10 AWG

Ordering details
Description

Color

Type

with 2 test sockets DIA 2 mm
0,079 in

Disconnect

Grey

ZS6-S-4S-T2

Main technical data

Part Number
1SNK506316R0000

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
27 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 V
IP20

1 conductor
per clamp

35.7 1.40"

6 mm 0.236 in spacing

59.8 2.35"

52.9 2.08"

67.3 2.64"

60.4 2.38"

3Weight(1 pce) g

50

18.40

Mounting instructions

Connecting capacity
ZS6-S-4S-T

80.7 3.18"

Pkg
qty

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
28 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque300 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

10 mm
0.394 in0.087 in
2.2 mm41 A (IEC)2 poles
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
20
20
20
10
10
1680
22
20
10

14.00
3.10
1.30
2.10
2.90
3.60
7.40
5.20
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

1SNK161071S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS10-S screw clamp terminal blocks
Disconnect with blade - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver,–– Same profile as ZS10 feed-through terminal block for aligned marking and identical end section use.

Ordering details

1SNK161058F0014

Description

Color
Profile aligned with ZS10

Disconnect

Grey
Blue

26.7 1.05"

8 mm 0.315 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"

53 2.09"

Part Number

ZS10-S
ZS10-S-BL

1SNK508315R0000
1SNK508320R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

8.60
8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 10 mm²0.22 ... 10 mm²0.22 ... 10 mm²0.22 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
25 A / 4 mm²
42 A / 10 mm²
480 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

1 conductor
per clamp

ZS10-SType

24 ... 12 AWG
24 ... 12 AWG
20 ... 12 AWG

TH 35-7.5,
TH 35-15
12 mm
0.472 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
25 A / 6 AWG

3

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque300 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161050S0201

1

Technical data valid for copper conductors only.

PAGE 111

ZS4-SP screw clamp terminal blocks
Disconnect with plug - 5.2 mm 0.205 in spacing
4 mm²
10 AWG

Description–– Save time with our screwless component holder plug,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

Ordering details
Description
1SNK161023F0014

Disconnect

Color
Profile aligned with ZS4, plug delivered separetely

73.5 2.89"

56.3 2.22"
26.7 1.05"

48.8 1.92"
81 3.19"

53 2.09"

3

Grey

ZS4-SP

Main technical data

Part Number
1SNK505313R0000

Pkg

Weightqty(1 pce) g

50

8.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

ZS4-SPType

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
18 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing

CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2
3

3

5

4

6

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
Shield connectors
Component plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey

Dark grey
OrangeWhite

GreyPart Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
SHBS
1SNK900600R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
20
1960
22
20
10

14.00
2.20
1.80
6.00
3.50
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161033S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-SP-T2 screw clamp terminal blocks
Disconnect with plug - with test socket - 5.2 mm 0.205 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets DIA 2 mm 0.079 in,–– Save time with our screwless component holder plug,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

10 AWG

Ordering details
1SNK161036F0014

Description
Disconnect

Color

Type

Profile aligned with ZS4, with 2 test
sockets DIA 2 mm 0.079 in, plugdelivered separetely

Grey

ZS4-SP-T2

1SNK505314R0000

Main technical data

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"

53 2.09"

Pkg

Weightqty(1 pce) g

50

8.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

ZS4-SP-T2

Part Number

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
18 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriver3

Ø 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 126.7 1.05"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2
3

3

5

4

6

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
Shield connectors
Component plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey

Dark grey
OrangeWhite

GreyPart Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
SHBS
1SNK900600R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
20
1960
22
20
10

14.00
2.20
1.80
6.00
3.50
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161041S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

PAGE 113

ZS4-SP-R1 screw clamp terminal blocks
Disconnect with plug - 6 mm 0.236 in spacing
Description

4 mm²–– Simplify the alternated distribution between feed-through and disconnect circuits thanks to the two aligned
jumper channels,–– Save time with our screwless component holder plug.

10 AWG

Ordering details
1SNK161022F0014

Description
Disconnect

Color
Profile aligned with ZS4-SF, plugdelivered separetely

70.5 2.78"

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"

3

Grey

ZS4-SP-R1

Main technical data

Part Number
1SNK506313R0000

Pkg

Weightqty(1 pce) g

50

14.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

ZS4-SP-R1

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 126.7 1.05"

6 mm 0.236 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2

3

4
3

5

7

6

8

4
5
6
7
8

Color

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 polesTest adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inComponent plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
20
20
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
3.50
3.50
0.27
10.00
11.00
0.20

1SNK161039S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-SP-T2-R1 screw clamp terminal blocks
Disconnect with plug - with test socket - 6 mm 0.236 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets DIA 2 mm 0.079 in,–– Save time with our screwless component holder plug,–– Simplify the distribution between feed-through and disconnect circuits thanks to the two aligned jumper
channels.

1SNK161037F0014

10 AWG

Ordering details
Description
Disconnect

Color

Type

Profile aligned with ZS4-SF, with 2
test sockets DIA 2 mm 0.079 in,plug delivered separetely

Grey

ZS4-SP-T2-R1

1SNK506314R0000

Main technical data

ZS4-SP-T2-R1

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"
26.7 1.05"

6 mm 0.236 in spacing

Pkg

Weightqty(1 pce) g

50

14.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

70.5 2.78"

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 in3

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2

5

7

4

6

3
4
5
6
7

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 polesTest connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmComponent plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
20
20
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
3.50
3.50
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161040S0201

3

Color

Technical data valid for copper conductors only.

PAGE 115

ZS10-SP screw clamp terminal blocks
Disconnect with plug - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Save time with our screwless component holder plug,–– Same profile as ZS10 feed-through terminal block for aligned marking and identical end section use.

Ordering details
Description
1SNK161060F0014

Disconnect

Color
Profile aligned with ZS10

Grey

56.3 2.22"

326.7 1.05"

48.8 1.92"

53 2.09"

ZS10-SP

Main technical data

Part Number
1SNK508316R0000

Pkg

Weightqty(1 pce) g

50

8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 10 mm²0.22 ... 10 mm²0.22 ... 10 mm²0.22 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
18 A / 2.5 mm²
18 A / 10 mm²
300 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 VIP20

300 V

1 conductor
per clamp

ZS10-SPType

24 ... 8 AWG
24 ... 8 AWG
20 ... 12 AWG

Tool

20 ... 12 AWG
18 A / 6 AWG
TorqueTH 35-7.5,
TH 35-15
12 mm
0.472 inFlat screwdriverØ 4 mmØ 0.157 in

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

CE

RoHS

USR

CSA

EAC

Accessories
1

3

4

1
2
3
4
5

End stops
End sections
Component plugs
Disconnect plugs
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 inComponents in series with circuit
Equipped with linking bar
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
1680
22
20
10

14.00
2.20
3.50
3.50
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161051S0201

5

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPB-85

3

PAGE 117

SNK series, terminal blocks
Fuse protection
Optimize your control circuit protection
Our SNK series fuse terminal blocks offer a full set of featuresand functions to protect your control circuits with efficiency
and reliability.
All terminal blocks complies with the latest evolution of theinternational standards IEC 60947-7-3 (“Ancillary equipment
safety requirements for fuse terminal blocks.”) which fixes
precise temperature constraint for short-circuit and overload
protection (information in the catalogue pages related to the
products).
Qualified for worldwide markets and applications
Eco-designed according to international environmental
standards in sustainable development.
3
CE

RoHS
EAC

Select the right fuse holder for the right application

2 Expert for convenient circuit distribution
The expert fuse holders are equipped with two central jumper
channels for convenient common distribution and are alignedwith feed-through and disconnect terminal blocks. They
facilitate alternated potential distribution and reduce wiring.
Additional features for easy trouble shooting and testing
Performant blown fuse indicators
Low leakage current (< 0.5 mA) allows the protection of low
current circuits such as PLC’s inputs without any risk of circuit
disturbances.
Large voltage range (24/110 V and 110/250 V AC/DC) reduces the number of variants and allows adaptation to worldwide
applications (24/110 V range covers North american market
needs).
Easy testingSome terminal blocks are equipped with Dia 2 mm built-in
test socket screws for circuit testing while respecting the IP20
touch proof protection.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1

2

5x20 and 5x25 mm fusesCompact and high density

5x20 and 6.3x32 mm fuses
Easy potential distribution

Low leakage current blown fuseindicator.
Large voltage range: (24/110 V and
110/250 V AC and DC)

Convenient testing through built in
test socket screws

1SNK161085S0201

1 standard applications
The standard fuse holders feature compact dimensions while
offering compatibility with 5 x 20 and 5 x 25 mm fuses.
double deck terminal blocks allow efficient space reduction
for panels with space constraints.

SNK series, terminal blocks
Marshalling cabinets application
The smart choice for process
automation
Large process automation applications typically require theuse of a large number of digital or analog signals and sensors.
Indeed, marshalling cabinets ensure an important cross wiring
function, since the incoming field signal and the channel
quantity of the I/O card of the controller (DCS, large PLC’s) isalways different. They facilitate the maintenance operations
and ease the system modifications.
SNK aligned terminal blocks offering:
SNK series now features a full set of aligned terminal blocks
matching the marshalling panels typical configurations. Fuse,disconnect, feed-through and ground terminal blocks withidentical profile are providing compact and convenient solution. With only 6 mm spacing, two aligned screwless jumper
channels, central large marking as well as aligned conductor
entries, they are perfectly adapted to alternative potential
distribution while still easy to connect.

3

Typical marshalling configurations
Digital signals

AnalogPopular potential distribution via double centerchannel.

Disconnect functions equipped with test
points allow total isolation of circuits, easecircuit testing during start-up, test and maintenance operations.

+

-

+

-

+

-

Potential distribution for analog signals.
Ground terminal blocks allow reliable connection of cable shields to the ground sparing theuse of external shield bar.

5
1

3

4

1

ZS4-R2

Load

Load

Load

2

ZS4-SF

3

Load

Load

ZS4-S-R1 or ZS4-S-R2

Load

4

Load

ZS4-PE-R2

Load

5

JB6-...

PAGE 1191SNK161086S0201

2
Load

ZS4-SF1 screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - 8 mm 0.315 in spacing
Description

4 mm²

Protect your circuit with 5x25 and 5x20 fuse terminal blocks, compliant with IEC 60947-7-3 standard (fusenot supplied with the terminal blocks).

10 AWG

Ordering details

1SNK161007F0014

Description

59.7 2.35"

54.6 2.15"

47.1 1.85"

90°

180°

88.8 3.5"

90°

3

Type
ZS4-SF1ZS4-SF1-OR

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthMain technical data

Pkg

Part Number

Grey, dark grey
Orange, dark
grey

Fuse

1SNK508410R0000
1SNK508430R0000

Weightqty(1 pce) g

50
50

13.30
13.30

Mounting instructions

1 conductor
per clamp

ZS4-SF1

96.3 3.79"

Color

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

3

4

5

6

1
2
3
4

Color

5

End stops
10 mm
End sections
1.5 mmLateral jumper bars 10 poles
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings

0.394 in0.059 in35 A (IEC)6

Neutral cartridge

5x25

7

Terminal block
markers

Blank marker
Blank card

White

Universal wire markers holder

Grey

Dark grey
Dark grey
Grey

Type

Part Number

Pkg

Weightqty(1 pce) g

14.00
1.80
5.00
1.00
1.50
2.00

BAM4
ES4-SFPC81-10
TGA8
TGA8
TGA8
ANT

1SNK900001R0000
1SNK508960R0000
1SNA173523R1100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400

50
20
10
10
10
10
10

CN5

1SNA179371R1600

10

3.9

1680
22
20
10

0.27
10.00
14.00
0.20

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161011S0201

7

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-SF1-T screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket - 8 mm 0.315 in spacing
Description

4 mm²–– Protect your circuit with 5x25 and 5x20 fuse terminal blocks (fuse not supplied with the terminal blocks),–– Compliant with IEC 60947-7-3 standard,–– With built in test sockets.

10 AWG

1SNK161041F0014

Ordering details

47.1 1.85"

90°

180°

54.6 2.15"

90°

59.7 2.35"

88.8 3.5"

Color

With 2 test sockets DIA 2 mm 0.079 in

Type

Pkg

Part Number

Grey, dark grey

ZS4-SF1-T2

1SNK508411R0000

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthFuse

Main technical data

Weightqty(1 pce) g

50

13.30

Mounting instructions

1 conductor
per clamp

ZS4-SF1-T

96.3 3.79"

Description

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG

3Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories

3

4

5

6

7

Description

2
1
2
3
4

Color

5

End stops
10 mm
End sections
1.5 mmLateral jumper bars 10 poles
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings

0.394 in0.059 in35 A (IEC)6

Neutral cartridge

5x25

7

Terminal block
markers

Blank marker
Blank card

White

Universal wire markers holder

Grey

Dark grey
Dark grey
Grey

Type

Part Number

Pkg

Weightqty(1 pce) g

14.00
1.80
5.00
1.00
1.50
2.00

BAM4
ES4-SFPC81-10
TGA8
TGA8
TGA8
ANT

1SNK900001R0000
1SNK508960R0000
1SNA173523R1100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400

50
20
10
10
10
10
10

CN5

1SNA179371R1600

10

3.9

1680
22
20
10

0.27
10.00
14.00
0.20

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161036S0201

1

Technical data valid for copper conductors only.

PAGE 121

ZS4-SF1-R screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator - 8 mm 0.315 in spacing
4 mm²
10 AWG

Description–– Protect your circuit with 5x25 and 5x20 fuse terminal blocks (fuse not supplied with the terminal blocks),–– Compliant with IEC 60947-7-3 standard,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
1SNK161042F0014

Description
Fuse

Color

With blown fuse indicator 115 … 250 V
AC / DC
With blown fuse indicator 24 … 110 V
AC / DCType

Grey, dark grey

47.1 1.85"

90°88.8 3.5"

54.6 2.15"

90°
96.3 3.79"

180°(1 pce) g

1SNK508414R0000

50

13.30

ZS4-SF1-R1

1SNK508412R0000

50

13.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

59.7 2.35"

3Weightqty

ZS4-SF1-R3

Main technical data

ZS4-SF1-R

Pkg

Part Number

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

2

3

4

5

6

Description
1
2
3
4
5
6

Color

End stops
10 mm
0.394 in0.059 inEnd sections
1.5 mm35 A (IEC)
Lateral jumper bars 10 poles
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
Grey

White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
ANT
1SNA168675R1400
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
1680
22
20
10

14.00
1.80
5.00
1.00
1.50
2.00
0.27
10.00
14.00
0.20

1SNK161034S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-SF1-R screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator and test sockets - 8 mm 0.315 in spacing
Description

4 mm²
10 AWG–– Protect your circuit with 5x25 and 5x20 fuse terminal blocks (fuse not supplied with the terminal blocks),–– Compliant with IEC 60947-7-3 standard,–– Ease the test with built-in test sockets,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

1SNK161043F0014

Ordering details
Description

Color

Type

Fuse With blown fuse indicator 115 … 250 V AC / DC Grey, dark grey
and 2 test sockets DIA 2 mm 0.079 inWith blown fuse indicator 24 … 110 V AC / DCand 2 test sockets DIA 2 mm 0.079 in

Pkg

Part Number
1SNK508415R0000

50

13.30

ZS4-SF1-R2

1SNK508413R0000

50

13.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15
11 mm
0.432 in

ZS4-SF1-R

1 conductor
per clamp

32.9 1.30"

47.1 1.85"

54.6 2.15"

90°

90°
88.8 3.5"

96.3 3.79"

180°(1 pce) g

ZS4-SF1-R4

Main technical data

59.7 2.35"

Weightqty

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

3Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 18 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
Description

2

3

4

1
2
3
4

5

6

5
6

Color

End stops
10 mm
0.394 in0.059 inEnd sections
1.5 mmLateral jumper bars 10 poles
35 A (IEC)
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
Grey

White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
ANT
1SNA168675R1400
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
1680
22
20
10

14.00
1.80
5.00
1.00
1.50
2.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161035S0201

1

Technical data valid for copper conductors only.

PAGE 123

ZS4-R1 screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

4 mm²

Simplify the alternated feed-through and fuse circuits operations:–– With the same profile as the ZS4-SF1, the wiring of the alternated feed-through and fuse circuits is easier.

10 AWG

Ordering details

1SNK161046F0014

Description
Feed-throughColor
Profile aligned with ZS4-SF1

Grey

59.7 2.35"

32.9 1.30"

8 mm 0.315 in spacing

38.6 1.52"

46.1 1.82"

3

ZS4-R1Main technical data

Pkg

Part Number
1SNK508013R0000

Weightqty(1 pce) g

50

11.00

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
24 A / 2.5 mm²
300 A

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

ZS4-R1Type

800 V
6000 V
IP20

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
26 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

3

Description

2

4

1
2
3
4

Color

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A (IEC)
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
Grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
1680
22
20
10

14.00
1.80
5.00
0.27
10.00
14.00
0.20

Fuse screw clamp terminal blocks
Description
Fuse

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color
Grey, dark greyType
ZS4-SF1

Part Number
1SNK508410R0000

Pkg

Weightqty(1 pce) g

50

13.30

1SNK161009S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS4-S-R3 screw clamp terminal blocks
Disconnect with lever - 8 mm 0.315 in spacing
Description

4 mm²

Simplify the disconnect operations for the disconnect terminal blocks installed next to fuse terminal blocks ZS4-SF1:–– With the same profile as ZS4-SF1, the ZS4-S-R3 disconnect lever is easily operated by hand and the wiringof the alternated disconnect and fuse circuits is easier.,–– Neutral cartridge CN5 5x25 included.

10 AWG

1SNK161032F0014

Ordering details
Description
Disconnect

Color
Profile aligned with ZS4-SF1

Type

Grey, orange
Grey, blue

ZS4-S-R3ZS4-S-R3-T2

Main technical data

47.1 1.85"

90°88.8 3.5"

180°

54.6 2.15"

90°
96.3 3.79"

59.7 2.35"

1SNK508416R0000
1SNK508419R0000

Weightqty(1 pce) g

50
50

13.30
13.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
18 A / 2.5 mm²
18 A / 4 mm²
300 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

1 conductor
per clamp

ZS4-S-R3

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriver

Tool

3

Ø 3.5 mm
Ø 0.138 in

24 ... 14 AWG
18 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect lever does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

BV

EAC

DNV

Rina

Accessories
Description

2

3

4

5

6

1
2
3
4
5
6

Color

End stops
10 mm
0.394 in0.059 inEnd sections
1.5 mmLateral jumper bars 10 poles
35 A (IEC)
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
Grey

White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
ANT
1SNA168675R1400
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
1680
22
20
10

14.00
1.80
5.00
1.00
1.50
2.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Fuse screw clamp terminal blocks
Description
Fuse

Color
Grey, dark greyType
ZS4-SF1

Part Number
1SNK508410R0000

Pkg

Weightqty(1 pce) g

50

13.30

Technical data valid for copper conductors only.

PAGE 125

1SNK161044S0201

1

ZS4-SF screw clamp terminal blocks
For 5 x 20 fuses - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks.

Ordering details
1SNK161021F0014

Description

Color

ZS4-SF

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthMain technical data3

86.3 3.40"

78.8 3.10"

70.3 2.77"

Pkg

Part Number

Grey, dark grey

Fuse

1SNK506410R0000

Weightqty(1 pce) g

50

18.60

Mounting instructions

1 conductor
per clamp

ZS4-SFType

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

150 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.

26.7 1.05"

6 mm 0.236 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

1

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

4

6

Color
10 mm
0.394 in41 A (IEC)2 poles
3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161005S0201

Accessories

ZS4-SF-T screw clamp terminal blocks
For 5 x 20 fuses - with test socket - 6 mm 0.236 in spacing
4 mm²

1SNK161038F0014

10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks,–– Ease the test with built-in test socket screws.

Ordering details
Description

Color

ZS4-SF-T2

1SNK506411R0000

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthMain technical data

86.3 3.40"

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG(1 pce) g

50

18.60

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriver

Tool

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection3

Ø 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

78.8 3.10"

70.3 2.77"

Weightqty

Mounting instructions

1 conductor
per clamp

ZS4-SF-T

Pkg

Part Number

Grey, dark grey

Fuse

With 2 test sockets DIA 2 mm 0.079 in

Type

150 V
NEMA 126.7 1.05"

6 mm 0.236 in spacing

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories

3

5

Description

2
1
2

End stops
Jumper bars

3
4
5

Test connectors
Spacers
Terminal block
markers

4

Color
10 mm
0.394 in41 A (IEC)2 poles
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)End module, 5.2 mm 0.205 in
0.031 in
0.8 mmBlank marker
Blank card

Dark grey

Universal wire markers holder

Grey

OrangeDark grey
Dark grey
White

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK161038S0201

1

Technical data valid for copper conductors only.

PAGE 127

ZS4-SF-R screw clamp terminal blocks
For 5 x 20 fuses - with blown fuse indicator - 6 mm 0.236 in spacing
4 mm²

1SNK161039F0014

10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
Description
Fuse

Color

With blown fuse indicator 115 … 250 V
AC / DC
With blown fuse indicator 24 … 110 V
AC / DCType

Grey, dark grey

86.3 3.40"

78.8 3.10"

70.3 2.77"

50

18.60

ZS4-SF-R1

1SNK506412R0000

50

18.60

Mounting instructions
IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
length24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque26.7 1.05"

6 mm 0.236 in spacing(1 pce) g

1SNK506415R0000

Connecting capacity
1 conductor
per clamp

3

Weightqty

ZS4-SF-R3

Main technical data
ZS4-SF-R

Pkg

Part Number

500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

150 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Description

2

3

4

5

6

1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

Color
10 mm
0.394 in41 A (IEC)2 poles
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.031 in
0.8 mmBlank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161006S0201

Accessories
1

ZS4-SF-R screw clamp terminal blocks
For 5 x 20 fuses - with blown fuse indicator and test sockets - 6 mm 0.236 in spacing
4 mm²

1SNK161040F0014

10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks,–– Ease the test with built-in test socket screws,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
Description
Fuse

ZS4-SF-R

Color

With blown fuse indicator 115 … 250 V
AC / DC and 2 test sockets DIA 2 mm
0.079 inWith blown fuse indicator 24 … 110 V
AC / DC and 2 test sockets DIA 2 mm
0.079 inType

Grey, dark grey

Pkg

Part Number
1SNK506416R0000

50

18.60

ZS4-SF-R2

1SNK506413R0000

50

18.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15
10.5 mm0.412 in70.3 2.77"

86.3 3.40"

1 conductor
per clamp

78.8 3.10"(1 pce) g

ZS4-SF-R4

Main technical data

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

Ø 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

3

Flat screwdriver

Tool

24 ... 16 AWG
10 A / 10 AWG

26.7 1.05"

6 mm 0.236 in spacing

Weightqty

150 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

1

3

5

Description

2
1
2

End stops
Jumper bars

3
4
5

Test connectors
Spacers
Terminal block
markers

4

Color
10 mm
0.394 in41 A (IEC)2 poles
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)End module, 5.2 mm 0.205 in
0.031 in
0.8 mmBlank marker
Blank card

Dark grey

Universal wire markers holder

Grey

OrangeDark grey
Dark grey
White

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

PAGE 129

1SNK161037S0201

Accessories

ZS4-R2 screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²–– Simplify the distribution of circuits in marshalling cabinets thanks to our feed-through terminal blocks withthe same profile as ZS4-SF fuse, ZS4-S-R1 disconnect and ZS4-PE-R2 ground terminal blocks: aligned
conductor entries, jumper channels and marking in just 6 mm 0.236 in spacing,–– No end section needed: closed block.

10 AWG

1SNK161074V0014

Ordering details
Description
Feed-through

Color

Type

Profile aligned with ZS4-SF and
ZS4-S-R1

Grey

ZS4-R2Main technical data

70.5 2.77"

48.8 1.92"

56.3 2.22"

3

1SNK506013R0000

Pkg

Weightqty(1 pce) g

50

12.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp

ZS4-R2

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
30 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 126.7 1.05"

6 mm 0.236 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2

3

5

4

6

3
4
5
6
7

7

Color

10 mm
0.394 in
2 poles
41 A (IEC)
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmTerminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB85-3
1SNK900603R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
2.80
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Screw clamp terminal blocks
Fuse
ZS4-SFZS4-S-R1

Disconnect

Color
Profile aligned with ZS4-R2 andZS4-PE-R2
Profile aligned with ZS4-R2 andZS4-PE-R2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Type

Grey, dark grey
Grey

Part Number

Pkg

Weightqty(1 pce) g

ZS4-SF

1SNK506410R0000

50

18.60

ZS4-S-R1

1SNK506310R0000

50

13.20

1SNK161083S0201

Description

ZS4-PE-R2 screw clamp terminal blocks
Ground - 6 mm 0.236 in spacing
Description

4 mm²

Simplify the shielding connection of your analog circuits in marshalling cabinets thanks to our ground terminal
blocks with the same profile as ZS4-SF fuse, ZS4-S-R1 disconnect and ZS4-R2 feed-through terminal blocks.

10 AWG

Ordering details
1SNK161089V0014

Description

Color
Screwless rail connection

GroundType

Green-yellow

ZS4-PE-R2

1SNK506153R0000

IEC

UL - CSA

Rail

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A3-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data

ZS4-PE-R2

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

25

15.30

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
396 A

Protection

IP20

NEMA 1

TH 35-7.5,
TH 35-15
10.5 mm0.413 inØ 3.5 mm
Ø 0.138 in
3

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque48.8 1.92"

56.3 2.22"

Weight(1 pce) g

Flat screwdriverTool
77 3.03"26.7 1.05"

Pkg
qty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing

CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

Color

End stops
End sections
Terminal block
markers

10 mm
0.394 in
2.2 mm0.087 in
Blank marker
Blank card

Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
1680
22
20
10

14.00
3.10
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Screw clamp terminal blocks
Fuse
ZS4-SFZS4-S-R1

Disconnect

Color
Profile aligned with ZS4-R2 andZS4-PE-R2
Profile aligned with ZS4-R2 andZS4-PE-R2

Type

Grey, dark grey
Grey

Part Number

Pkg

Weightqty(1 pce) g

ZS4-SF

1SNK506410R0000

50

18.60

ZS4-S-R1

1SNK506310R0000

50

13.20

Technical data valid for copper conductors only.

PAGE 131

1SNK161079S0201

Description

ZS4-S-R2 screw clamp terminal blocks
Disconnect with lever - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description
Simplify the disconnect operations for the disconnect terminal blocks installed next to fuse terminal blocks ZS4-SF:–– With the same profile as ZS4-SF, the ZS4-S-R2 disconnect lever is easily operated by hand and the wiringof the alternated disconnect and fuse circuits is easier.

Ordering details
1SNK161033F0014

Description

Color
Profile aligned with ZS4-SF

Disconnect

Grey, orange

3

86.3 3.40"
26.7 1.05"

6 mm 0.236 in spacing

78.8 3.10"

70.3 2.77"

ZS4-S-R2

Main technical data

Pkg

Part Number
1SNK506414R0000

Weightqty(1 pce) g

50

21.6

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²
18 A / 4 mm²
300 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

ZS4-S-R2

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
13 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect lever does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

4

6

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Fuse screw clamp terminal blocks
Description
Fuse

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color
Grey, dark greyType
ZS4-SF

Part Number
1SNK506410R0000

Pkg

Weightqty(1 pce) g

50

18.60

1SNK161043S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS10-SF screw clamp terminal blocks
For 6.3x32 fuses - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Protect your circuits with 6.3x32 (¼ x 1¼ in) fuse terminal blocks compliant with IEC 60947-7-3 standard(fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels.

Ordering details
1SNK161071F0014

Description

Color

ZS10-SF

1SNK508418R0000

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
10 A / 10 mm²

24 ... 6 AWG

Wire stripping
lengthMain technical data

74.3 2.93"

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

85.3 3.36"

Weight(1 pce) g

50

28.50

630 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
22 A / 6 AWG

3

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque77.8 3.06"

Pkg
qty

Mounting instructions

1 conductor
per clamp

ZS10-SF

Part Number

Grey, dark grey

Fuse

Closed block

Type

600 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

26.7 1.05"

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

8 mm 0.315 in spacing

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

4W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

2.5 W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

DNV

Accessories
Description

2

3

4

5

6

1
2

End stops
Jumper bars

3

Test adapters

4

Test connectors

56Spacers
Terminal block
markers

Color
10 mm
0.394 in
2 poles
57 A (IEC)3 poles
57 A (IEC)57 A (IEC)4 poles
5 poles
57 A (IEC)57 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
0.110 in
2.8 mmBlank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
40
20
20
20
10
10
10
1680
22
20
10

14.00
2.70
4.10
5.60
7.00
14.20
1.70
2.40
5.20
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161052S0201

1

Technical data valid for copper conductors only.

PAGE 133

ZS10-SF-R screw clamp terminal blocks
For 6.3x32 fuses - with blown fuse indicator - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Protect your circuits with 6.3x32 (¼ x 1¼ in) fuse terminal blocks compliant with IEC 60947-7-3 standard(fuse not supplied with the terminal blocks),–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
1SNK161073F0014

Description
Fuse

Color

With blown fuse indicator 115 … 250 V
AC / DC
With blown fuse indicator 24 … 110 V
AC / DCType

Grey, dark grey

8 mm 0.315 in spacing

77.8 3.06"

85.3 3.36"
26.7 1.05"

50

30.50

ZS10-SF-R1

1SNK508421R0000

50

30.50

Mounting instructions
IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
10 A / 10 mm²

24 ... 6 AWG

Wire stripping
length24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

630 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
22 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque600 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement
1

Weight(1 pce) g

1SNK508422R0000

Connecting capacity
1 conductor
per clamp

74.3 2.93"

3

Pkg
qty

ZS10-SF-R3

Main technical data

ZS10-SF-R

Part Number

Assembly composed of 5 fuse terminal blocks

2

Overload and short-circuit
protection

4W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

2.5 W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

3

4

CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Description
5

6

1
2

End stops
Jumper bars

3

Test adapters

4

Test connectors

56Spacers
Terminal block
markers

Color
10 mm
0.394 in
57 A (IEC)2 poles
57 A (IEC)3 poles
4 poles
57 A (IEC)57 A (IEC)
5 poles
10 poles
57 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
2.8 mm0.110 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
40
20
20
20
10
10
10
1680
22
20
10

14.00
2.70
4.10
5.60
7.00
14.20
1.70
2.40
5.20
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161053S0201

Accessories

ZS10-S-R2 screw clamp terminal blocks
Disconnect with lever - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description
Simplify the disconnect operations for the disconnect terminal blocks installed next to fuse terminal blocks ZS10-SF:–– With the same profile as ZS10-SF, the ZS10-S-R2 disconnect lever is easily operated by hand and the wiringof the alternated disconnect and fuse circuits is easier.

Ordering details
1SNK161070F0014

Description

Color
Profile aligned with ZS10-SF

Disconnect

Grey, orange

ZS10-S-R2

Main technical data

ZS10-S-R2

77.8 3.06"

74.3 2.93"

Part Number
1SNK508417R0000

Pkg

Weightqty(1 pce) g

50

35.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
10 A / 4 mm²
25 A / 10 mm²
480 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

1 conductor
per clamp

85.3 3.36"

Type

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
22 A / 25 AWG

3

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque600 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect lever does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.

26.7 1.05"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4

Test connectors

56Spacers
Terminal block
markers

4

6

Color
10 mm
0.394 in
2 poles
57 A (IEC)3 poles
57 A (IEC)57 A (IEC)4 poles
5 poles
57 A (IEC)57 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
0.110 in
2.8 mmBlank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
40
20
20
20
10
10
10
1680
22
20
10

14.00
2.70
4.10
5.60
7.00
14.20
1.70
2.40
5.20
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Fuse screw clamp terminal blocks
Description
Fuse

Color
Closed block

Grey, dark grey

Type
ZS10-SF

Part Number
1SNK508418R0000

Pkg

Weightqty(1 pce) g

50

28.50

Technical data valid for copper conductors only.

PAGE 135

1SNK161055S0201

1

ZS4-D2 screw clamp terminal blocks
Double deck with 2 feed-through circuits - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 5.2 mm 0.205 in spacing,–– Customize yourself the ZS4-D2 by soldering electronic components (up to 8.8 mm x 3.2 mm 0.346 x 0.125in) in the existing linking bars punching.

Ordering details
1SNK161014F0014

Description
2 feed-through circuits

36.8 1.45"

67 2.64"74.5 2.94"

70.4 2.77"

Type

Grey
Blue
OrangePkg

Part Number

ZS4-D2ZS4-D2-BL
ZS4-D2-OR

Main technical data

1SNK505210R0000
1SNK505220R0000
1SNK505230R0000

Weightqty(1 pce) g

50
50
50

15.30
15.30
15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 20 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS4-D2

3Feed-throughColor

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing

CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

1SNK161003S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-D1 screw clamp terminal blocks
Double deck with 1 feed-through circuit - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description–– Ease one potential distribution on 4 independent screw clamps,–– Save space by connecting conductors up to 4 mm² (CB certified) 12 AWG in just 5.2 mm 0.205 in spacing.

Ordering details
Description
1SNK161015F0014

Feed-throughColor
1 feed-through circuit

Grey

67 2.64"74.5 2.93"

70.4 2.77"

Pkg

Part Number

ZS4-D1

1SNK505211R0000

Main technical data

Weightqty(1 pce) g

50

15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 20 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS4-D1Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

3

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

36.8 1.45"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161007S0201

1

Technical data valid for copper conductors only.

PAGE 137

ZS6-D2 screw clamp terminal blocks
Double deck with 2 feed-through circuits - 6 mm 0.236 in spacing
6 mm²

1SNK161010F0014

10 AWG

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 6 mm 0.236 in spacing,–– Customize yourself the ZS6-D2 by soldering electronic components (up to 8.8 mm x 3.2 mm 0.346 x 0.125in) in the existing linking bars punching,–– Boost the performances: ZS6-D... with ES4-D2 end section is rated 1000 V DC IEC, perfectly adapted tosolar applications.

Ordering details
Description
Feed-throughColor
2 feed-through circuits

Type

Grey
Blue
OrangeYellow
Red
White
Black

ZS6-D2ZS6-D2ZS6-D2-BL
ZS6-D2-OR
ZS6-D2-YL
ZS6-D2-RD
ZS6-D2-WH
ZS6-D2-BK

Main technical data3

70.4 2.77"

67 2.64"74.5 2.94"

6 mm 0.236 in spacing

1SNK506210R0000
1SNK506220R0000
1SNK506230R0000
1SNK506260R0000
1SNK506262R0000
1SNK506265R0000
1SNK506266R0000

Weightqty(1 pce) g

50
50
50
50
50
50
50

18.40
18.40
18.40
18.40
18.40
18.40
18.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
40 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 40 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 30 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

36.8 1.45"

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
0.100 in2.55 mm2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in4

Test adapters

5
6
7
8

Test connectors
Spacers
Shield connectors
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
SHB
1SNK900602R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
20
20
20
10
10
20
1680
22
20
10

24.00
4.10
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
4.90
0.27
10.00
11.00
0.20

Ground screw clamp terminal blocks
Description
GroundProfile aligned with ZS6-D2 and ZS6-D1

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

ColorGreen-yellow

Type
ZS6-D1-PE

Part Number
1SNK506250R0000

Pkg

Weightqty(1 pce) g

20

18.40

1SNK161014S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS6-D1 screw clamp terminal blocks
Double deck with 1 feed-through circuit - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description–– Ease one potential distribution on 4 independent screw clamps,–– Save space by connecting conductors up to 6 mm² 10 AWG in just 6 mm 0.236 in spacing,–– Boost the performances: ZS6-D... with ES4-D2 end section is rated 1000 V DC IEC, perfectly adapted tosolar applications.

1SNK161009F0014

Ordering details
Description
Feed-through

Color

Type

1 feed-through circuit

Grey
Red

ZS6-D1ZS6-D1-RD

1SNK506211R0000
1SNK506214R0000

Main technical data

36.8 1.45"

67 2.64"74.5 2.93"

70.4 2.77"

Weightqty(1 pce) g

50
50

18.40
18.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
40 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 40 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 30 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS6-D1

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriver

Tool

3

Ø 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing

CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in4

Test adapters

5
6
7
8

Test connectors
Spacers
Shield connectors
Terminal block
Blank marker
markers
Blank card

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
SHB
1SNK900602R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
20
20
20
10
10
20
1680
22
20
10

24.00
4.10
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
4.90
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161013S0201

1

Technical data valid for copper conductors only.

PAGE 139

ZS6-D2-PE screw clamp terminal blocks
Double deck with 1 feed-through circuit and 1 ground circuit - 6 mm 0.236 in spacing
Description

6 mm²–– Save space with ZS6-D2-PE terminal blocks: 1 feed-through circuit and 1 ground circuit in just 6 mm 0.236
in spacing,–– Customize yourself the ZS6-D2-PE terminal blocks by soldering electronic components (up to 8.8 mm x
3.2 mm 0.346 x 0.125 in) in the existing linking bars punching.

10 AWG

1SNK161061F0014

Ordering details
Description

Color

Type

Feed-through + 1 feed-through circuit and 1 groundcircuitgroundGrey

ZS6-D2-PE

Main technical data

77.1 3.03"

36.8 1.45"

6 mm 0.236 in spacing

67 2.64"74.5 2.94"

3

1SNK506212R0000

Pkg

Weightqty(1 pce) g

50

18.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²0.22 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
41 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

ZS6-D2-PE

Part Number

800 V
8000 V
IP20

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
10 mm
0.393 inFlat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2

3

4

5

6

1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Test adapters
Test connectors
Spacers
Terminal block
markers

7

Color
10 mm
0.394 in2.55 mm0.100 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
20
20
10
10
1680
22
20
10

24.00
4.10
1.30
2.10
2.90
3.60
7.40
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Feed-through screw clamp terminal blocks
Description
Feed-throughColor
2 feed-through circuits

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Type
Grey

ZS6-D2

Part Number
1SNK506210R0000

Pkg

Weightqty(1 pce) g

50

18.40

1SNK161048S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS6-D1-PE screw clamp terminal blocks
Double deck with 1 ground circuit - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description–– Save space with double deck ground terminal blocks aligned with ZS6-D2 double deck terminal blocks forconvenient cabling process and circuit configuration,–– Benefit from our screwless rail connection: non operator independant, secured snap on or remove from therail, performances above the requirements of IEC 60947-7-2 standard.

1SNK161062F0014

Ordering details
DescriptionColor
1 ground circuit

GroundType

Green-yellow

ZS6-D1-PE

1SNK506250R0000

IEC

UL - CSA

Rail

0.2 ... 6 mm²0.22 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data

ZS6-D1-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

20

18.40

Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

10 AWG

Protection

IP20

NEMA 1

TH 35-7.5,
TH 35-15
10 mm
0.393 in

Ø 4 mmØ 0.157 in

3

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque67 2.64"74.5 2.94"

Weight(1 pce) g

Flat screwdriver

Tool
77.1 3.03"

36.8 1.45"

Pkg
qty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing

CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

10 mm
0.394 in2.55 mm0.100 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
1680
22
20
10

24.00
4.10
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161049S0201

3

End stops
End sections
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 141

ZS4-D2-S screw clamp terminal blocks
Double deck with 1 disconnect circuit and 1 feed-through circuit - 5.2 mm 0.205 in spacing
4 mm²
10 AWG

Description–– Save space: connect one complete circuit on a single block featuring disconnect and feed-through for the
return circuit in just 5.2 mm 0.205 in spacing,–– Same profile as ZS4-D... double deck terminal blocks: convenient cabling process, aligned jumpers, markers and common end section.

1SNK161095V0014

Ordering details
Color

Feed-through + 1 disconnect circuit and 1 feedthrough circuit
disconnect

77.3 3.04"

71.1 2.8"

78.6 3.09"

84.8 3.34"

70.4 2.77"

Type
Grey

ZS4-D2-S

Main technical data

Part Number
1SNK505315R0000

Pkg

Weightqty(1 pce) g

50

15.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

ZS4-D2-S

3

Description

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG

25 A / 4 mm²

27 A / 10 AWG

29 A / 4 mm²
480 A
630 V
8000 V
IP20

27 A / 10 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 136.8 1.45"

5.2 mm 0.205 in spacing

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2

3

4

5

6

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
0.100 in2.55 mm2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

4

Test adapters

5
6

Shield connectors
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
SHB
1SNK900602R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
20
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
4.90
0.23
9.00
10.00
0.20

1SNK161074S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-D2-S-T screw clamp terminal blocks

Double deck with 1 disconnect circuit with test socket screws and 1 feed-through circuit - 5.2 mm 0.205 in spacing

4 mm²
10 AWG

Description
Find the same functionalities as ZS4-D2-S, upgraded with the two built-in test socket screws meant to ease
your signal testing during commissioning and maintenance.

Ordering details

1SNK161099V0014

Description

Color

Feed-through + 1 disconnect circuit with 2 test
socket screws and 1 feed-throughdisconnect
circuit36.77 1.45"

5.2 mm 0.205 in spacing

77.3 3.04"

71.1 2.8"

84.8 3.34"

78.6 3.09"

70.4 2.77"

Grey

ZS4-D2-S-T2

Main technical data

Part Number
1SNK505316R0000

Pkg

Weightqty(1 pce) g

50

16.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp
ZS4-D2-S-T

Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG

25 A / 4 mm²

27 A / 10 AWG

29 A / 4 mm²
480 A
630 V
8000 V
IP20

27 A / 10 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 in3

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
Description

2

3

4

5

6

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

4

Test adapters

5
6

Shield connectors
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
SHB
1SNK900602R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
20
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
4.90
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161075S0201

1

Technical data valid for copper conductors only.

PAGE 143

ZS4-D2-SF1 screw clamp terminal blocks
Double deck with 1 fuse circuit and 1 feed-through circuit - 8 mm 0.315 in spacing
Description

4 mm²–– Save space: connect one complete circuit on a single block featuring fuse and feed-through for the return circuit,–– Protect your circuit with either 5X20 or 5X25 fuse (fuse not supplied with the terminal blocks),–– High performances product: compliant with IEC 60947-7-3 standard and jumper channel for the feedthrough circuit.

10 AWG

Ordering details
1SNK161096V0014

Description
1 fuse circuit and 1 feed-throughcircuit89.2 3.51"

83 3.27"
68 2.68"

124.7 4.91"
109.7 4.32"

90°
90°

180°

Type

Part Number

Grey, dark grey

ZS4-D2-SF1

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section

0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

Feed-through+ fuseMain technical data

1SNK508425R0000

Pkg

Weightqty(1 pce) g

50

27.50

Mounting instructions

1 conductor
per clamp

ZS4-D2-SF1

3

Color

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG

6.3 A / 4 mm²

12 A / 10 AWG

32 A / 4 mm²

30 A / 10 AWG

800 V
8000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in

Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

NEMA 1

48.2 1.90"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

1

Description

2
1
2
3

3

4

5

6

4
5
6

7

9

8

7
8
9

Color

10 mm
0.394 in
2.5 mm
0.098 in
2 poles
57 A (IEC)57 A (IEC)3 poles
4 poles
57 A (IEC)57 A (IEC)
5 poles
10 poles
57 A (IEC)35 A (IEC)
Lateral jumper bars 10 poles
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 inSpacers
2.8 mm0.110 in
Assembly rods
2 poles
3 poles
4 poles
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeGrey
Dark grey
Dark grey
Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2-SF1
1SNK508911R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
PC81-10
1SNA173523R1100
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
40
20
10
20
20
10
10
10
10
10
10
1680
22
20
10

24.00
5.00
2.70
4.10
5.60
7.00
14.20
5.00
1.70
2.40
5.20
5.20
1.40
1.00
1.50
2.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161076S0201

Accessories

ZS4-D2-SF1-R screw clamp terminal blocks
Double deck with 1 fuse circuit with blown fuse indicator and 1 feed-through circuit - 8 mm 0.315 in spacing
Description

4 mm²–– Find the same functionalities as ZS4-D2-SF1, upgraded with our integrated blown fuse indicator (with leakage current < 0.5 mA),–– Only one part number needed to fit AC / DC 24 V up to 110 V.

10 AWG

Ordering details

1SNK161097V0014

Description
Feed-through+ fuse

Color

Type

Grey, dark grey
1 fuse circuit with blown fuseindicator 115 ... 250 V AC / DC and
1 feed-through circuit
1 fuse circuit with blown fuseindicator 24 ... 110 V AC / DC and 1
feed-through circuit

83 3.27"
68 2.68"

124.7 4.91"
109.7 4.32"

90°
90°

180°

48.2 1.90"

8 mm 0.315 in spacing

50

29.40

ZS4-D2-SF1-R1

1SNK508423R0000

50

29.40

Mounting instructions
IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section

0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection
Separatearrangement

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

6.3 A / 4 mm²

12 A / 10 AWG

32 A / 4 mm²

30 A / 10 AWG

800 V
8000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in3

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG

Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

NEMA 1

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Weight(1 pce) g

1SNK508424R0000

Connecting capacity
1 conductor
per clamp

89.2 3.51"

Pkg
qty

ZS4-D2-SF1-R3

Main technical data
ZS4-D2-SF1-R

Part Number

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

BV

EAC

DNV

1

Description

2
1
2
3

3

4

5

6

4
5
6

7

9

8

7
8
9

Color

10 mm
0.394 in
0.098 in
2.5 mm57 A (IEC)2 poles
3 poles
57 A (IEC)57 A (IEC)4 poles
5 poles
57 A (IEC)57 A (IEC)
10 poles
Lateral jumper bars 10 poles
35 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
0.110 inSpacers
2.8 mmAssembly rods
2 poles
3 poles
4 poles
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeGrey
Dark grey
Dark grey
Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2-SF1
1SNK508911R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
PC81-10
1SNA173523R1100
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
40
20
10
20
20
10
10
10
10
10
10
1680
22
20
10

24.00
5.00
2.70
4.10
5.60
7.00
14.20
5.00
1.70
2.40
5.20
5.20
1.40
1.00
1.50
2.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

PAGE 145

1SNK161077S0201

Accessories

ZS4-T3 screw clamp terminal blocks
Triple deck with 3 feed-through circuits - 5.2 mm 0.205 in spacing
Description

4 mm²
12 AWG

Save space: 3 independent circuits in just 5.2 mm 0.205 in spacing,–– Fit many applications: space constraints, multiple signals distribution, sensors distribution, thanks to thejumper channels available on each deck.

Ordering details
1SNK161087V0014

Description
Feed-throughColor
3 feed-through circuits

Grey

87.4 3.44"
55.3 2.17"

5.2 mm 0.205 in spacing

79.9 3.14

100.1 3.94"

3

ZS4-T3Main technical data

Part Number
1SNK505212R0000

Pkg

Weightqty(1 pce) g

25

24.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²

24 ... 12 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp

ZS4-T3Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2

3

4

5

6

1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5
6

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

Dark grey
Dark grey
OrangeDark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-T3
1SNK505961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
100
1960
22
20
10

24.00
4.20
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
0.73
0.23
9.00
10.00
0.20

1SNK161072S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-T3-R1 screw clamp terminal blocks
Triple deck with 3 feed-through circuits - 6 mm 0.236 in spacing
Description

4 mm²
10 AWG

Unique triple deck solution combining increased connecting capacity ( up to 4 mm² with ferrule) and jumper
channel available on each deck,–– Fit many applications: space constraints, multiple signals distribution, sensors distribution,–– Closed terminal block: no end section needed, optimized rigidity.

1SNK161088V0014

Ordering details
Description
Feed-through

Color
Closed block with 3 feed-throughcircuits

87.4 3.44"

79.9 3.14"

100.1 3.94"

Grey

Part Number

ZS4-T3-R1

1SNK506213R0000

Main technical data

Pkg

Weightqty(1 pce) g

50

28.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp

ZS4-T3-R1

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriver

Tool

3

Ø 3.5 mm
Ø 0.138 in

24 ... 16 AWG
30 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

55.3 2.17"

6 mm 0.236 in spacing
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4
5

Label holders
Terminal block
markers

4

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)
41 A (IEC)4 poles
5 poles
41 A (IEC)
41 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

Dark grey
OrangeDark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
LH-J
1SNK900606R0000
MG-CPM 13 41791 1SNB041791R0612
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
50
50
50
50
20
20
20
100
1680
22
20
10

24.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
0.73
0.27
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161073S0201

1

Technical data valid for copper conductors only.

PAGE 147

ZS4-D-CH-UD screw clamp terminal blocks
Component holder - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details
Description

1SNK161141V0014

Component
holderColor
Cathode of the blocking diodeconnected to the lower circuit

Grey

3

67 2.64"74.5 2.94"

70.4 2.77"

ZS4-D-CH-UD

Main technical data

Part Number
1SNK505214R0000

Pkg

Weightqty(1 pce) g

50

15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
length1 conductor
per clamp

ZS4-D-CHType

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 12 AWG
Torque

800 V

300 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
10 mm
0.393 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

36.8 1.45"

5.2 mm 0.205 in spacing

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

1SNK161090S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSZS4-D-CH-DU screw clamp terminal blocks
Component holder - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details
Description

1SNK161142V0014

Component
holderColor
Cathode of the blocking diodeconnected to the upper circuit

Grey

67 2.64"74.5 2.94"

70.4 2.77"

Part Number

ZS4-D-CH-DU

1SNK505215R0000

Main technical data

Pkg

Weightqty(1 pce) g

50

15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
length1 conductor
per clamp

ZS4-D-CHType

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 12 AWG
Torque

800 V

300 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
10 mm
0.393 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
3

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

36.8 1.45"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)
32 A (IEC)4 poles
5 poles
32 A (IEC)
32 A (IEC)
10 poles
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161091S0201

1

Technical data valid for copper conductors only.

PAGE 149

SNK series, terminal blocks
Screw clamp technology - Test & measurement

Secure your measurement operations
The new ZS10-ST test & measurement terminal blocks benefit fromour long experience in the energy applications and from the SNKfeatures: performances, ergonomy, common
accessories and marking.

High performances– – 10 mm² 6 AWG– – 6 mm² 10 AWG with ferrule– – 50 A (IEC) 53 A (UL– – Worldwide certifications

3

RoHS

BV

EAC

Rely on our smart design
Insulated short circuit bridges:
SC-JB8Insulated captive test sockets:
AJS9
6 colorscompatible with standard
DIA. 4 mm test plugs(IEC 60010-031)

Circuit separators: CS
For visual separation between
CT & PT circuits

Protecting cover kits: KCO

New ground terminal block:

Lateral jumper bar: PC8
For CT or PT commoning

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160057S0201

ZS10-PE-R1

Guarantee accessonly to authorized operators

cover can be permanently sealed with a seal or cable tie.
Centering drilling guide for seal or cable tie.
The cover is specially designed to ease its mounting or removal:– – Hook shape on each side for convenient removal with screwdriver

Assembly with protecting cover

Drilling and centering guide3

Seal with cable tie

Convenient removal with screwdriver

CT sidePT sidesliding link status: closed

Disconnect sliding link status:
Open and close symbols help tovisualize the sliding link position

sliding link status: opened

Measuring equipment side

1 Fully operated by screwdriver (DIA 3.5 mm)
2 Short-circuited position secured thanks to AJS9 test sockets tightening
3 Adapted hook shape maintain the bridge on terminal block in the1

2

3

non connected position

PAGE 151

1SNK160057S0201

Short-circuit CT circuits safely andconveniently

SNK series, terminal blocks
Test & measurement - Typical schematic for measuring devices

Common point on the transformers
CT's
P1

L1
P1

L2
L3

PT's

P1
S1

P2 S1

P2 S1

P2
S2

S2

S2

P

P

P

S

S

S

1

2

3
3

N

N

Current inputs

Voltage inputs
Measuring devices(ie: meters, protection relays…)

Bill of material with convenient customization(test sockets, feed-through terminals…)

Bill of material optimized

CT's

PT's

CT's

PT's

7
5

1
Description

2
Type

1
Order code

Qty needed
CT’s

1 Terminal block

ZS10-ST-T4

2 End section
3 Short-circuit bridges

62

Description

4

3

Type

Order codePT’s

2
Qty needed
CT’s

PT’s

1SNK508311R0000 6

41 Terminal block

ZS10-ST-T4

1SNK508311R0000 3

0

ES10-ST

1SNK508910R0000 1

1

2 Terminal block

ZS10-R1

1SNK508011R0000 3

1

SC-JB8-2

1SNK900652R0000 3

0

3 Terminal block

ZS10-ST-1

1SNK508312R0000 0

3

4 End section

ES10-ST

1SNK508910R0000 1

1

5 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 30

6 Test socket

AL4-M3

1SNA206721R0100 0

1

7 Insulated test socket

AJS9

1SNA179726R0200 3

0

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160058S0201

3

SNK series, terminal blocks
Test & measurement - Typical schematic for measuring devices

Common point on the terminal block assembly
CT's

L1
P1

L2
L3

PT's
P1

P1
S1

P2 S1

P2 S1

P2
S2

S2

S2

P

P

P

S

S

S

3

2

1

3

N

N

Current inputs

Voltage inputs

Measuring devices(ie: meters, protection relays…)

Bill of material with convenient customization(test sockets, feed-through terminals…)

Bill of material optimized
4

CT's

9

PT's

CT's

PT's

8
5

6
7

Description

2 3
Type

Order code1
Qty needed
CT’s2

Description

4 5

3

Type

Order codePT’s

2
Qty needed
CT’s

PT’s

1 Terminal block

ZS10-ST-T4

1SNK508311R0000 6

41 Terminal block

ZS10-ST-T4

1SNK508311R0000 3

0

2 Terminal block

ZS10-PE-R1 1SNK508151R0000 1

0

2 Terminal block

ZS10-R1

1SNK508011R0000 3

1

3 End section

ES10-ST

1SNK508910R0000 1

1

3 Terminal block

ZS10-ST-1

1SNK508312R0000 0

3

4 Lateral jumper bars

PC8-R1

1SNA400711R0600 1

0

4 Terminal block

ZS10-PE-R1 1SNK508151R0000 1

0

5 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 3

0

5 End section

ES10-ST

1SNK508910R0000 1

1

6 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 30

7 Test socket

AL4-M3

1SNA206721R0100 0

1

8 Insulated test socket

AJS9

1SNA179726R0200 30

9 Lateral jumper bars

PC8-R1

1SNA400711R0600 1

0PAGE 153

1SNK160058S0201

1

ZS10-ST screw clamp terminal blocks
Test disconnect with sliding link - 8 mm 0.315 in spacing
Description

10 mm²–– Secure your disconnect operations in control circuits with the robust sliding link operated with a screwdriver,–– Customize ZS10-ST with colored test sockets in order to identify conveniently each phase of the Current
Transformer or Potential Transformers secondary circuits,–– Fully compatible with the ZS10-ST-T4 accessories.

6 AWG

1SNK161065F0014

Ordering details
Description

Color

DisconnectGrey80.7 3.18"

61 2.40"

53.5 2.11"

3Part Number

ZS10-ST

1SNK508310R0000

Main technical data

Pkg

Weightqty(1 pce) g

25

24.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
50 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 V
IP20

1 conductor
per clamp

ZS10-STType

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 12 AWG
53 A / 6 AWG

Torque300 V

Disconnect device
Tool
TorqueNEMA 1

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
1.3 Nm ± 0.3
11.5 lb.in ± 2.65
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in

38.7 1.52"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

4
5

Color

10 mm
0.394 in
2 mm
0.079 in
2 poles
50 A (IEC)3 poles
50 A (IEC)
50 A (IEC)4 poles
5 poles
50 A (IEC)
50 A (IEC)
10 polesCircuit separators 3 mm
0.118 in
Test sockets
Test sockets DIA 4 mm 0.157 in
End stops
End sections
Jumper bars

Type

Dark grey
Dark grey
OrangeDark grey
Yellow
Black
Green
Grey
Blue
Red
White
PurpleBrown

6

Terminal block
markers

DIA 4 mm 0.157 in - H=12 mm 0.492 in - M3 screw
Blank marker
Blank card

White

Universal wire markers holder

GreyPart Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
JB8-2-R1
1SNK908902R0000
JB8-3-R1
1SNK908903R0000
JB8-4-R1
1SNK908904R0000
JB8-5-R1
1SNK908905R0000
JB8-10-R1
1SNK908910R0000
CS-R3
1SNK900107R0000
AJS9
1SNA179726R0200
AJS9-BK
1SNA206680R1500
AJS9-GN
1SNA206681R0200
AJS9-GR
1SNA206682R0300
AJS9-BL
1SNA206683R0400
AJS9-RD
1SNA206720R1400
AJS9-WH
1SNA206765R0000
AJS9-PR
1SNA206772R0000
AJS9-BR
1SNA206782R0000
AL4-M3
1SNA206721R0100
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
20
25
25
25
25
25
25
25
25
25
50
1680
22
20
10

14.00
3.5
7.6
11.6
15.5
19.4
39.00
6.40
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
1.10
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description

ZS10-R1

ZS10-PE-R1

Feed-throughGroundColor
Profile aligned with ZS10-ST...
Profile aligned with ZS10-ST...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

GreyGreen-yellow

Type
ZS10-R1
ZS10-PE-R1

Part Number
1SNK508011R0000
1SNK508151R0000

Pkg

Weightqty(1 pce) g

25
25

20.90
28.40

1SNK161056S0201

Screw clamp terminal blocks

ZS10-ST-1 screw clamp terminal blocks
Test disconnect with sliding link for Potential Transformer circuits - 8 mm 0.315 in spacing
Description

10 mm²

Test terminal blocks especially designed for Potential Transformers circuits:–– low profile voltage measurement thanks to the two compact built-in test sockets compatible with DIA 4 mm
0.157 in test plugs,–– Installed with our aligned feed-through and ground terminal blocks, you benefit of a complete and compact
solution for your PT circuits.
1SNK161069F0014

6 AWG

Ordering details
Description

Color

Type

With 2 test sockets DIA 4 mm
0.157 in

Disconnect

Grey

ZS10-ST-1

1SNK508312R0000

Main technical data
ZS10-ST-1

61 2.40"

53.5 2.11"

38.7 1.52"

8 mm 0.315 in spacing

Pkg

Weightqty(1 pce) g

25

27.00

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
50 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 VIP10

1 conductor
per clamp

80.7 3.18"

Part Number

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 12 AWG
53 A / 6 AWG

Torque300 V

Disconnect device
Tool
TorqueNEMA 1

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
1.3 Nm ± 0.3
11.5 lb.in ± 2.65
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in

3

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

4
5
6
7

7

Color

End stops
10 mm
0.394 in0.079 inEnd sections
2 mm
Lateral jumper bars 10 poles
4/6 poles
4/8 poles
4/10 poles
3/4 poles
4/7 poles
2/3 poles
4/6 poles
4/8 poles
Circuit separators 3 mm
0.118 inProtecting cover kits
Protecting covers 1 m 39.4 in length
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark greyBlack

Dark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
PC8-10
1SNA163313R2400
PC8-R1
1SNA400711R0600
PC8-R2
1SNA400712R0700
PC8-R3
1SNA400713R0000
PC8-R4
1SNA400724R0300
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
KCO
1SNK900624R0000
CO
1SNK900604R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
1
1
1680
22
20
10

14.00
3.5
14.00
6.60
7.80
9.00
4.50
6.60
6.60
6.60
7.80
6.40
47.80
300.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Screw clamp terminal blocks

ZS10-R1

ZS10-PE-R1

Feed-throughGroundColor
Profile aligned with ZS10-ST...
Profile aligned with ZS10-ST...

Grey
Green-yellow

Type
ZS10-R1
ZS10-PE-R1

Part Number
1SNK508011R0000
1SNK508151R0000

Pkg

Weightqty(1 pce) g

25
25

20.90
28.40

Technical data valid for copper conductors only.

PAGE 155

1SNK161062S0201

Description

ZS10-ST-T4 screw clamp terminal blocks
Test disconnect with sliding link for Current Transformer circuits - 8 mm 0.315 in spacing
Description

10 mm²

Test terminal blocks especially designed for Current Transformers circuits:–– easy and safe current measurement thanks to the two insulated built-in test sockets compatible with IP20
DIA 4 mm 0.157 in test plugs (per IEC60101-031),–– convenient short-circuit operations with the SC-JB insulated sliding bridges.

6 AWG

Ordering details
1SNK161066F0014

Description

Color
With two yellow test sockets DIA
4 mm 0.157 in

Disconnect

80.7 3.18"

62.6 2.46"

70.1 2.76"

61 2.40"

53.5 2.11"

3

Grey

Part Number

ZS10-ST-T4

1SNK508311R0000

Main technical data

Pkg

Weightqty(1 pce) g

25

31.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
50 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 V
IP20

1 conductor
per clamp

ZS10-ST-T4

Type

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 12 AWG
53 A / 6 AWG

Torque300 V

Disconnect device
Tool
TorqueNEMA 1
Test socket
Tool

38.7 1.52"

8 mm 0.315 in spacing

TorqueTH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
1.3 Nm ± 0.3
11.5 lb.in ± 2.65
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

End stops
10 mm
0.394 inEnd sections
2 mm
0.079 in
Lateral jumper bars 10 poles
4/6 poles
4/8 poles
4/10 poles
3/4 poles
4/7 poles
2/3 poles
4/6 poles
4/8 poles
Circuit separators 3 mm
0.118 inProtecting cover kits
Protecting covers 1 m 39.4 in length
Short circuit
2 polesbridges
3 poles
4 poles
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark greyBlack

Dark grey
Dark grey
Transparent
Yellow

White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
PC8-10
1SNA163313R2400
PC8-R1
1SNA400711R0600
PC8-R2
1SNA400712R0700
PC8-R3
1SNA400713R0000
PC8-R4
1SNA400724R0300
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
KCO
1SNK900624R0000
CO
1SNK900604R0000
SC-JB8-2
1SNK900652R0000
SC-JB8-3
1SNK900653R0000
SC-JB8-4
1SNK900654R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
1
1
25
25
25
1680
22
20
10

14.00
3.5
14.00
6.60
7.80
9.00
4.50
6.60
6.60
6.60
7.80
6.40
47.80
300.00
2.00
3.4
4.7
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description

ZS10-R1

ZS10-PE-R1

Feed-throughGroundColor
Profile aligned with ZS10-ST...
Profile aligned with ZS10-ST...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

GreyGreen-yellow

Type
ZS10-R1
ZS10-PE-R1

Part Number
1SNK508011R0000
1SNK508151R0000

Pkg

Weightqty(1 pce) g

25
25

20.90
28.40

1SNK161057S0201

Screw clamp terminal blocks

ZS10-R1 screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

10 mm²–– With the same profile as the ZS10-ST..., the feed-through ZS10-R1 allows you to fully implement the electrical drawing of your CT or PT circuits,–– Fully compatible with the ZS10-ST... accessories.

6 AWG

Ordering details
1SNK161068F0014

Description
Feed-throughColor
Profile aligned with ZS10-ST...

Grey

61 2.40"

53.5 2.11"

80.7 3.18"

Part Number

ZS10-R1

1SNK508011R0000

Main technical data

Pkg

Weightqty(1 pce) g

25

20.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
57 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
length1 conductor
per clamp

ZS10-R1

Type

630 V
8000 V
IP20

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

20 ... 12 AWG
62 A / 6 AWG

3

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque300 V
NEMA 138.7 1.52"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3
4

5

6

7

4

5
6
7

10 mm
0.394 in
2 mm
0.079 in
2 poles
50 A (IEC)3 poles
50 A (IEC)
50 A (IEC)4 poles
5 poles
50 A (IEC)
50 A (IEC)
10 poles
Lateral jumper bars 4/7 poles
2/3 poles
4/6 poles
4/8 poles
0.118 inCircuit separators 3 mm
Test sockets
Test sockets DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeBlack

Dark grey
Yellow
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
JB8-2-R1
1SNK908902R0000
JB8-3-R1
1SNK908903R0000
JB8-4-R1
1SNK908904R0000
JB8-5-R1
1SNK908905R0000
JB8-10-R1
1SNK908910R0000
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
AJS9
1SNA179726R0200
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
25
1680
22
20
10

14.00
3.5
7.6
11.6
15.5
19.4
39.00
6.60
6.60
6.60
7.80
6.40
3.60
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161059S0201

3

Color

Technical data valid for copper conductors only.

PAGE 157

ZS10-PE-R1 screw clamp terminal blocks
Ground - 8 mm 0.315 in spacing
Description

10 mm²–– With the same profile as the ZS10-ST..., the ground ZS10-PE-R1 allows you to fully implement the electricaldrawing of your CT or PT circuits,–– Fully compatible with the ZS10-ST... accessories,–– Short-circuit performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.
1SNK161067F0014

6 AWG

Ordering details
Description

Color
Profile aligned with ZS10-ST...

GroundType

Green-yellow

ZS10-PE-R1

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²
A5-B5

24 ... 6 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

61 2.40"3

53.5 2.11"

83.7 3.29"

1SNK508151R0000

Pkg

Weightqty(1 pce) g

25

28.40

Mounting instructions

Connecting capacity

ZS10-PE-R1

Part Number

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 8 AWG
24 ... 10 AWG

Flat screwdriver

Tool
Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

TH 35-7.5,
TH 35-15
13 mm
0.512 inØ 3.5 mm
Ø 0.138 in

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque38.7 1.52"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

4

5
6
7

Color

10 mm
0.394 in
2 mm
0.079 in
2 poles
50 A (IEC)3 poles
50 A (IEC)
50 A (IEC)4 poles
5 poles
50 A (IEC)
50 A (IEC)
10 poles
Lateral jumper bars 4/7 poles
2/3 poles
4/6 poles
4/8 poles
0.118 inCircuit separators 3 mm
Test sockets
Test sockets DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeBlack

Dark grey
Yellow
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
JB8-2-R1
1SNK908902R0000
JB8-3-R1
1SNK908903R0000
JB8-4-R1
1SNK908904R0000
JB8-5-R1
1SNK908905R0000
JB8-10-R1
1SNK908910R0000
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
AJS9
1SNA179726R0200
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
25
1680
22
20
10

14.00
3.5
7.6
11.6
15.5
19.4
39.00
6.60
6.60
6.60
7.80
6.40
3.60
0.27
10.00
14.00
0.20

1SNK161058S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPB-125

3

PAGE 159

Summary_4

4

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal blocks
Pluggable technology
Technologies presentation			

162

Overview				

168

PI-Spring Pluggable
Pluggable Pluggable
2.5 mm² / 12 AWG

Feed-throughZD2.5-11
ZD2.5-22

172
173

Ground

ZD2.5-22-PE

174

Feed-through

175
176
177

PI-Spring Pluggable
2.5 mm² / 12 AWG

		

ZDK2.5-11
ZDK2.5-21
ZDK2.5-22

4 mm² / 10 AWG

Feed-throughZDK4-22178

2.5 mm² / 12 AWG

GroundZDK2.5-11-PE
ZDK2.5-22-PE

179
180

Double deck

ZDK2.5-D2
ZDK2.5-D1
ZDK2.5-D2-PE

181
182
183

		

ZDK2.5-D1-PE

184

PI-Spring female plugs

CDK2.5
CDK2.5-J
CDK2.5-2P-J
CDK4

185
186
187
188

4 mm² / 10 AWG
Feed-through		

ZDS4-22
ZDS4-22-R1

190
192

Screw clamp female plugs

CDS4
CDS4-R1

191
193

		

4

Summary_4

Screw clamp Pluggable

PAGE 161

Pluggable technology - SNK series, terminal blocks
Features and benefits

The SNK series pluggable terminal blocks combine the benefits of our smart connections with the flexibility ofthe pluggable function.

PI-Spring Pluggable

Speed up your projects
Modularity brings assembly flexibility
Pluggable technology brings modularity into the electrical installation
allowing the combination of sub-assemblies and prewired harnesses
that facilitate and considerably accelerate assembly test and factorycommissioning.

PI-Spring Pluggable

Better project identification– Circuit identification is improved thanks to the 20% larger marking area
– Pre-mark by hand or with label on our flat marking surface
and start immediately the wiring, before the final markers mounting

4– Spare markers re-printing in case of modifications.

Pluggable Pluggable

Clear circuit identification

1SNK164014S0201 - Rev. A

Screw clamp Pluggable

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSubassemblies

1

T
TES

ED

Subassemblies

Subassemblies

1 Serialize plugs harnesses
Instead of one to one wiring, the wires are combined in one
single harness. Production and testing of harnesses can beserialized and outsourced.

2

2 Mounting time reduced by 90%
Reduce the mounting and testing time of the whole
equipment by connecting subassemblies with pluggableterminal blocks and harnesses. Ease the factorycommissioning.

Control panel

4
3 Disconnect for transportation
Easily disconnect the harnesses if needed for convenienttransportation of big equipment.

4 Quickly secure on-site reconnection
Secure oan-site installation: final reconnection is done in few
quick steps and fully secured thanks to error-free coding
system. Facilitate the final commissioning.

3

1SNK164014S0201 - Rev. A

4

PAGE 163

Pluggable technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process
Mounting, wiring, testing… made easy.
Create your own assemblies without tooling:– Easily snap together multiple plugs– Eliminate stock of pre-configured plugs.

Only two plug variants are required to compose harnesses up to 15 poles

Some plugs feature a jumper channel and/or 2 connections
that ease the signal distribution or wiring daisy chaining ofsubassemblies.

4

Easy signal distribution on plugs

Safety and protection
Eliminate connection errors with coding pegs:– Simply insert the pegs to create a coding sequence.
Secure your wiring against accidental tearing:– Automatic locking function– Lock safely 2 to 8 plugs with only one locking device– Cable clamp secures the wires onto the plug when pulling the plugassembly.
Cable clamp & locking device

1SNK164014S0201 - Rev. A

Convenient coding pegs

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal blocks
Features and benefits

Faster accessories mounting
Save up to 70% mounting time thanks to:– Screwless jumpers, component plugs, test devices, end stops
and snap-in ground terminal blocks.

Closed jumper location allows great stiffness of the terminal block,
avoid deflection while tightening and optimal jumper guiding.

Screwless accessories

Closed jumper location for stiffness

Snap-in ground terminal blocks

4

Smart accessories
Flexible test solutions from individual insulated test adapter to test
connectors for complete assemblies testing.

Smart plug-in jumpers
Pre-cut poles removable by hand: clean cut.

– Direct plug-in into jumpers channels

Predefined shapes in molding to easily identify connected poles
with a pen.

– 5, 6, 8 mm spacing, mixing various spacing is possible

Insulated up to 1000 V (avoid use of separators).

Plug-in individual test adapter

Plug-in test connector

Pre-cut poles easy removableby handPredefined shape to identify
connected poles

PAGE 165

1SNK164014S0201 - Rev. A– 1000 V rating.

Pluggable technology - SNK series, terminal blocks
Features and benefits

Optimized logistics
Reduce your accessories inventory by up to 50%
SNK PI-Spring, screw and pluggable ranges sharethe same accessories.

Facilitate maintenance operations
Terminal blocks can be individually removed from a terminal
assembly equipped with markers: TE Connectivity markers become
independent after strip mounting. The markers remain on terminal
in any situation.
Markers are interchangable: the smaller marker can fit any bigger block.

4
Maintenance operations facilitated

Reliable in harsh conditions
Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…

Shared accessories for SNK PI-Spring, screw and pluggable ranges

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSRoHS

1SNK164014S0201 - Rev. A

CE

1SNK164014S0201 - Rev. A

4

PAGE 167

SNK series, terminal blocks
Pluggable technology - Range overview from 2.5 to 4 mm² – 12 to 10 AWG
PI-Spring Pluggable

Pluggable Pluggable

PI-Spring Pluggable

24Connections

Connections

Connections

3

4

Single deckFeed-throughSingle deckFeed-throughGroundSingle deckFeed-throughGroundSingle deckFeed-throughSingle deckFeed-throughGroundConnections

2

Connections

4

Plugs

Compact plug
Save up to 15%
in height

Jumper plugs
Plugs with 1 or 2 connection& jumper to ease potential
distribution

Reduced plug variants
Only two plugs variants
to create assemblies

Voltage test
Screwdriver entry point
accepts category II probes

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSScrew clamp Pluggable

2x2

4

Double deckFeed-throughGroundSingle deckFeed-throughConnections

Connections

4

Locking device
Secure plug andwiring against
accidental pulling

Cable clamp
Secure the wires ontov
the plug when pulling
the plug assembly
1SNK164013S0201

End section
No need of end section
between 2.5 and 4 mm2
terminal blocks

Convenient coding pegs
Guarantee error freeplugs insertion

PAGE 169

SNK series, terminal blocks
Pluggable technology

PI-Spring Pluggable

Singledeck
Feed-throughGroundFeed-throughGroundSection
2.5 mm²

12 AWG

4 mm²

10 AWG

ZD2.5-11

ZD2.5-22

ZD2.5-22-PE

ZDK2.5-11

ZDK2.5-21

ZDK2.5-22

ZDK2.5-11-PE

ZDK2.5-22-PE

ZDK4-22

Doubledeck
Feed-throughFeed-through+ groundGroundZDK2.5-D2-PE

ZDK2.5-D1-PE

Section
2.5 mm²

12 AWG

4 mm²

10 AWGZDK2.5-D2

PI-Springfemaleplugs

ZDK2.5-D1

ClosedClosedClosedClosedClosedClosedSection
2.5 mm²

12 AWG

CDK2.5

CDK2.5-E

4 mm²

10 AWG

CDK4

CDK4-E

CDK2.5-J

CDK2.5-J-E CDK2.5-2P-J CDK2.5-2P-J-E CDK2.5-PE

CDK2.5-PE-E

CDK2.5-J-PE

CDK2.5-J-PE-E CDK2.5-2P-J-PE CDK2.5-2P-J-PE

Screw clamp Pluggable

Screw
clamp
femaleplugs

Singledeck
Feed-throughSection
4 mm²

ClosedSection
10 AWG

clamp -

ZDS4-22
ZDS4-22-R1

Channels for jumpering or testing -4 mm²

test socket -INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Blown-fuse indicator -male pluggable clamp -10 AWG

CDS4
CDS4-R1

female pluggable clamp

CDS4-E

1SNK164018S0201

4

PI-Spring Pluggable

PB-171

4

PAGE 171

ZD2.5-11 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164014V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through2 connections

Grey

Type

Part Number

Pkg Weightqty (1 pce) g

ZD2.5-11

1SNK805016R0000

50

Main technical data

ZD2.5-11

61.6 2.43"

69.1 2.72"

46.1 1.81"

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inRated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

Tool (for flexible

conductor without
ferrule)Ø 3.5 mm
Ø 0.138 in

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
24.2 0.94"
CE

CB

RoHS

USR CNR

CSA

BV

EAC

5.2 mm 0.205 in spacing

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed
CDK2.5Color
1 pole1 poleGrey

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.

CDK2.5-E

Accessories
1

2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
1.5 mm
0.059 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-11
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R2
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805915R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900106R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

5.30
1.49
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164020S0201

4

53.6 2.09"

54.4 2.13"

5.66

ZD2.5-22 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164015V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through

GreyPart Number

Pkg Weightqty (1 pce) g

ZD2.5-22

1SNK805017R0000

50

Main technical data

47.5 1.85"

5.2 mm 0.205 in spacing

61.6 2.43"

101.9 3.98"

69.1 2.72"

46.1 1.81"

53.6 2.09"

ZD2.5-22

4 connections

Type

12.00

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

4

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

Female plugs
Description

CDK2.5

Female plugs
Female plugs withoutouter nubs - Closed

CDK2.5-E

Color
1 pole1 poleGrey

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1ED2.5-22
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805917R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

5.30
3.64
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 173

1SNK164021S0201

1

ZD2.5-22-PE PI-Spring pluggable terminal blocks
Ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164016V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color
4 connections

GroundGreen-yellow

Part Number

Pkg Weightqty (1 pce) g

ZD2.5-22-PE

1SNK805156R0000

50

Main technical data

69.1 2.72"

108.4 4.25"

61.6 2.43"

46.1 1.81"

53.6 2.09"

ZD2.5-22-PE

Type

14.80

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 147.5 1.85"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

CDK2.5-PE CDK2.5-PE-E

Color
1 pole1 poleTypePart Number

Pkg Weightqty (1 pce) g

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey
Dark grey

BAZ1
ED2.5-22
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805917R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
20
20
20
10
10
10
22
20
1960
10

Green-yellow

2.80
2.88

15 poles max.

Accessories
1

3

5

7

Description

2

4

6

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Test connectors

6
7

Coding pegs
Terminal block
markers

5.2 mm0.205 in
2.0 mm
0.079 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Blank marker
Universal wire markers holder

Dark grey
Dark grey
White

Grey

5.30
3.64
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164022S0201

4

ZDK2.5-11 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164017V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through2 connections

Grey
Blue

Type

Part Number

Pkg Weightqty (1 pce) g

ZDK2.5-11
ZDK2.5-11-BL

1SNK805015R0000
1SNK805025R0000

50
50

Main technical data
ZDK2.5-11

58.6 2.31"

66.1 2.60"

43 1.69"

50.5 1.98"

49.6 1.93"

23.3 0.91"

7.00
7.00

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
4NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

CDK2.5-E

CDK2.5-BL CDK2.5-BL-E

Female plugs
Female plugs withoutouter nubs - Closed
Female plugs
Female plugs withoutouter nubs - Closed

Color

Type

Part Number

Pkg Weightqty (1 pce) g

1 pole1 poleGrey

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

1 pole1 poleBlue

CDK2.5-BL
CDK2.5-BL-E

1SNK805742R0000
1SNK805743R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
1.5 mm
0.059 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-11
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R2
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805915R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900106R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

5.30
1.49
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 175

1SNK164023S0201

1

ZDK2.5-21 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164020V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through3 connections

Grey

Type

Part Number

Pkg Weightqty(1 pce) g

ZDK2.5-21

1SNK805014R0000

50

7.47

Main technical data
ZDK2.5-21

4

23.3 0.91"

5.2 mm 0.205 in spacing

66.1 2.60"
58.6 2.31"

50.5 1.98"
43 1.69"

65.1 2.56"

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed
CDK2.5Color
1 pole1 poleGrey

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.

CDK2.5-E

1

2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg
qty

Weight(1 pce) g

5.2 mm0.205 in
1.5 mm
0.059 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-21
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805914R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

5.30
1.90
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164025S0201

Accessories

ZDK2.5-22 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
Description

2.5 mm²

1SNK162093V0014

12 AWG–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible for convenient
testing.

Ordering details
Description
Feed-throughFeed-through

ZDK2.5-22

Color

Type

4 connections
4 connections

Grey
Blue

ZDK2.5-22
ZDK2.5-22-BL

1SNK805010R0000
1SNK805020R0000

UL - CSARail

Main technical data

66.1 2.60"
58.6 2.31"

50.5 1.99"
43 1.69"
47.5 1.87"

5.2 mm 0.205 in spacing

Pkg

Weightqty(1 pce) g

50
50

9.60
9.60

Mounting instructions

Connecting capacity
89.3 3.52"

Part numberIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

24 A / 2.5 mm²
300 A

22 A / 12 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

600 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

4

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDK2.5

CDK2.5-E

1 poleType
GreyPart number

Pkg

Weightqty(1 pce) g

2.80
2.80

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

Type

Part number

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
1960
22
20
10

5.30
3.15
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
3.57
0.23
9.00
10.00
0.20

15 poles max.

1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

5.2 mm0.205 in0.087 in
2.2 mm32 A (IEC)2 poles
32 A (IEC)3 poles
4 poles
32 A (IEC)
32 A (IEC)
5 poles
10 poles
32 A (IEC)
32 A (IEC)
50 polesCross spacing jumpers 3 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAZ1
1SNK900002R0000
EDK2.5-22
1SNK805910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
Technical data valid for copper conductors only.

PAGE 177

1SNK164001S0201

Accessories

ZDK4-22 PI-Spring pluggable terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²

1SNK162094V0014

10 AWG–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5-R1 + ES-TC6) withstanding 10 000 operations are compatible
for convenient testing.

Ordering details
Description
Feed-through

Color

Type

4 connections

ZDK4-22

1SNK806010R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey

Main technical data

ZDK4-2267.2 2.65"
59.7 2.35"

50.5 1.99"
43 1.69"
50.3 1.98"

6 mm 0.236 in spacing
4

Pkg

Weightqty(1 pce) g

50

14.30

Mounting instructions

Connecting capacity
93.8 3.69"

Part Number

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

30 A / 4 mm²
480 A

30 A / 10 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

600 V

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDK4

CDK4-E

1 poleType
GreyPart Number

Pkg

Weightqty(1 pce) g

3.80
4.50

CDK4
CDK4-E

1SNK806712R0000
1SNK806713R0000

50
50

Type

Part Number

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
10
1680
22
20
10

5.30
3.15
1.30
2.10
2.90
3.60
7.40
38.10
2.80
6.40
1.70
2.40
5.20
0.80
3.57
0.27
10.00
11.00
0.20

15 poles max.

1

Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

5.2 mm0.205 in0.087 in
2.2 mm41 A (IEC)2 poles
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)
41 A (IEC)
50 poles4 Cross spacing jumpers 3 poles
32 A (IEC)
0.118 in5 Circuit separators 3 mm
6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
End module, 5.2 mm 0.205 in
8 Spacers
0.8 mm
0.031 in9 Coding pegs
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAZ1
1SNK900002R0000
EDK2.5-22
1SNK805910R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164002S0201

Accessories

ZDK2.5-11-PE PI-Spring pluggable terminal blocks
Ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164019V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color
2 connections

GroundGreen-yellow

TypePart Number

Pkg Weightqty (1 pce) g

ZDK2.5-11-PE

1SNK805150R0000

50

Main technical data
ZDK2.5-11-PE

58.6 2.31"

66.1 2.60"

43 1.69"

50.5 1.98"

56.1 2.20"

9.62

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

4

24.2 0.94"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - ClosedColor
1 pole1 poleTypePart Number

Pkg Weightqty (1 pce) g

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey
Dark grey

BAZ1
EDK2.5-11
CS-R2
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805915R0000
1SNK900106R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
20
20
20
10
10
10
22
20
1960
10

Green-yellow

2.80
2.88

15 poles max.

CDK2.5-PE CDK2.5-PE-E

Accessories

3

5

7

Description

2

4

6

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Test connectors

6
7

Coding pegs
Terminal block
markers

5.2 mm0.205 in
1.5 mm
0.059 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Blank marker
Universal wire markers holder

Dark grey
Dark grey
White

Grey

5.30
1.49
3.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

1SNK164024S0201

1

Technical data valid for copper conductors only.

PAGE 179ZDK2.5-22-PE PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164022V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Color

Type

Part Number

Pkg Weightqty (1 pce) g

Green-yellow

ZDK2.5-22-PE

1SNK805152R0000

50

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Description
4 connections

Ground14.05

ZDK2.5-22-PE

Main technical data

47.5 1.85"

66.1 2.60"

58.6 2.31"

43 1.69"

50.5 1.98"

94.7 3.70"

Mounting instructions

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

5.2 mm 0.205 in spacing

4

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey
Dark grey

BAZ1
EDK2.5-22
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805910R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
20
20
20
10
10
10
22
20
1960
10

Color
1 pole1 poleGreen-yellow

2.80
2.88

15 poles max.

CDK2.5-PE CDK2.5-PE-E

Accessories

3

5

7

Description

2

4

6

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Test connectors

6
7

Coding pegs
Terminal block
markers

5.2 mm0.205 in
2.2 mm0.087 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Blank marker
Universal wire markers holder

Dark grey
Dark grey
White

Grey

5.30
3.15
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164026S0201

1

ZDK2.5-D2 PI-Spring pluggable terminal blocks
Double deck feed-through 2 circuits - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164023V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-throughdouble deck 4 connections

Grey
Blue

Type

Part Number

Pkg Weightqty (1 pce) g

ZDK2.5-D2
ZDK2.5-D2-BL

1SNK805213R0000
1SNK805223R0000

50
50

Main technical data
ZDK2.5-D2

85.2 3.35"

77.7 3.06"

69.6 2.72"

62.1 2.44"

81.5 3.19"

40.6 1.57"

5.2 mm 0.205 in spacing

11.89
11.89

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A
800 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
4NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

CDK2.5-E

CDK2.5-BL CDK2.5-BL-E

Female plugs
Female plugs withoutouter nubs - Closed
Female plugs
Female plugs withoutouter nubs - Closed

Color

Type

Part Number

Pkg Weightqty (1 pce) g

1 pole1 poleGrey

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

1 pole1 poleBlue

CDK2.5-BL
CDK2.5-BL-E

1SNK805742R0000
1SNK805743R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-D
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805913R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
White

Grey

5.30
3.88
1.30
2.00
2.70
3.50
7.10
36.00
2.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

PAGE 181

1SNK164029S0201

1

ZDK2.5-D1 PI-Spring pluggable terminal blocks
Double deck feed-through 1 circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164025V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-throughdouble deck 4 connections

Grey

Type

Part Number

Pkg Weightqty (1 pce) g

ZDK2.5-D1

1SNK805214R0000

50

Main technical data
ZDK2.5-D1

85.2 3.35"

77.7 3.06"

69.6 2.72"

4

62.1 2.44"

81.5 3.19"

12.46

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A
800 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

40.6 1.57"

5.2 mm 0.205 in spacing

CE

CB

RoHS

USR CNR

CSA

BV

EAC

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

1 pole1 pole

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Grey

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.
CDK2.5

CDK2.5-E

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-D
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805913R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
White

Grey

5.30
3.88
1.30
2.00
2.70
3.50
7.10
36.00
2.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164027S0201

1

ZDK2.5-D2-PE PI-Spring pluggable terminal blocks
Double deck feed-through + ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164027V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Grey, Greenyellow

ZDK2.5-D2-PE

1SNK805212R0000

50

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A
800 V
8000 V
IP20

Feed-through +grounddouble deck 4 connections

Main technical data
ZDK2.5-D2-PE

85.2 3.35"

77.7 3.06"

69.6 2.72"

62.1 2.44"

88.5 3.46"

40.6 1.57"

5.2 mm 0.205 in spacing

16.13

Mounting instructions

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
396 A
600 V
4

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

CDK2.5-E

CDK2.5-PE CDK2.5-PE-E

Female plugs
Female plugs withoutouter nubs - Closed
Female plugs
Female plugs withoutouter nubs - ClosedColor
1 pole1 poleGrey

1 pole1 poleGreen-yellow

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-D
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805913R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
White

Grey

5.30
3.88
1.30
2.00
2.70
3.50
7.10
36.00
2.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 183

1SNK164030S0201

1

ZDK2.5-D1-PE PI-Spring pluggable terminal blocks
Double deck ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164026V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color
double deck 4 connections

GroundGreen-yellow

TypePart Number

Pkg Weightqty (1 pce) g

ZDK2.5-D1-PE

1SNK805250R0000

50

Main technical data
ZDK2.5-D1-PE

88.5 3.46"

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

26 ... 14 AWG
26 ... 14 AWG

5.2 mm 0.205 in spacing

85.2 3.35"

77.7 3.06"

69.6 2.72"
40.6 1.57"

62.1 2.44"

conductor without
ferrule)4

16.80

Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

1 pole1 pole

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Green-yellow

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey

BAZ1
EDK2.5-D
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PAUMH

1SNK900002R0000
1SNK805913R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNK900611R0000

50
20
20
20
10
10
10
22
20
10

2.80
2.88

15 poles max.

CDK2.5-PE CDK2.5-PE-E

Accessories
1

3

5

Description

2

4

6

1
2
3

End stops
End sections
Test adapters

4

Test connectors

5
6

Coding pegs
Terminal block
markers

5.2 mm0.205 in
2.0 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Universal wire markers holder

Dark grey
Dark grey
White
Grey

5.30
3.88
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.20

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164028S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

CDK2.5 PI-Spring female plugs
Female plug - 5.2 mm 0.205 in spacing
Description

2.5 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDK2.5

1SNK160292V0014

1SNK160291V0014

12 AWG

CDK2.5-E

Ordering details
Description

Color

Female plugs
Female plugs without outer nubs - Closed

Type

Grey
Blue
Green-Yellow
Grey
Blue
Green-Yellow

CDK2.5
CDK2.5-BL
CDK2.5-PE
CDK2.5-E
CDK2.5-BL-E
CDK2.5-PE-E

1SNK805712R0000
1SNK805742R0000
1SNK805750R0000
1SNK805713R0000
1SNK805743R0000
1SNK805753R0000

IEC

UL - CSARail

Main technical data
19.1 0.75"

21.1 0.83"

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

36.2 1.43"

Pkg

Weightqty(1 pce) g

50
50
50
50
50
50

2.80
2.80
2.80
2.80
2.80
2.80

Mounting instructions

Connecting capacity

5.2 mm 0.205 in spacing

Part number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

24 A / 2.5 mm²
300 A

22 A / 12 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

600 V

11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

4

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41790 1SNB041790R0512
MG-CPMFA 43196 1SNB043196R0012
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1960
350
22
20
10

0.7
1.04
0.23
2.56
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK164005S0201

3

Locking devices
Cable clamp
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 185

CDK2.5-J PI-Spring female plugs
Female plug - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164001V0014

1SNK164000V0014

12 AWG

Description–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs
for optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in caseof needed modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.
Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Female plugs

Grey
Blue
Green-yellow
Grey
Blue
Green-yellow

CDK2.5-J
CDK2.5-J-BL
CDK2.5-J-PE
CDK2.5-J-E
CDK2.5-J-BL-E
CDK2.5-J-PE-E

1SNK805738R0000
1SNK805744R0000
1SNK805748R0000
1SNK805739R0000
1SNK805745R0000
1SNK805749R0000

50
50
50
50
50
50

Connecting capacity

IEC

UL - CSA

Rail

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A
800 V
8000 V
IP20

Female plugs without outer nubs - Closed
CDK2.5-J

CDK2.5-J-E

Main technical data

4

19.1 0.75"

5.2 mm 0.205 in spacing

42.9 1.65"

27.8 1.06"

23.8 0.91"

4.08
4.08
4.08
4.34
4.34
4.34

Mounting instructions

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
Description

2

3

4

5

6

1

Jumper bars

2

Test adapters

3

Test connectors

4
5
6

Locking devices
Strain Relief
Terminal block
markers

2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
32 A (IEC)
50 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
9.4 mm 0.370 in spacing
Blank card
Blank strip label
Blank marker
Universal wire markers holder

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Orange

JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50TP2
TP4
TC5
TC5-R1
VR-ZD
PT-ZD
MC512
MC512PA
MG-CPMFA 43196
MG-CPM 13 41790
UMH

1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900637R0000
1SNK900660R0000
1SNK140000R0000
1SNK149999R0000
1SNB043196R0012
1SNB041790R0512
1SNK900611R0000

50
50
50
50
30
10
20
20
10
10
50
50
22
20
400
1960
10

Dark grey
Dark greyBlack
Dark grey
White

Grey

1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.7
1.04
9.00
10.00
2.562
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164031S0201

1

CDK2.5-2P-J PI-Spring female plugs
Female plug - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164002V0014

1SNK164003V0014

12 AWG

CDK2.5-2P-J

CDK2.5-2P-J-E

35.5 1.38"

Description–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs
for optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in caseof needed modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.
Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Female plugs

Grey
Blue
Green-yellow
Grey
Blue
Green-yellow

CDK2.5-2P-J
CDK2.5-2P-J-BL
CDK2.5-2P-J-PE
CDK2.5-2P-J-E
CDK2.5-2P-J-BL-E
CDK2.5-2P-J-PE-E

1SNK805740R0000
1SNK805746R0000
1SNK805751R0000
1SNK805741R0000
1SNK805747R0000
1SNK805752R0000

50
50
50
50
50
50

Female plugs without outer nubs - Closed

29.8 1.14"
19.1 0.75"

5.2 mm 0.205 in spacing

44.9 1.73"

Main technical data

5.37
5.37
5.37
5.74
5.74
5.74

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A
500 V
6000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)4

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

1

Description

2

3

4

5

6

1

Jumper bars

2

Test adapters

3

Test connectors

4
5
6

Locking devices
Strain Relief
Terminal block
markers

2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
32 A (IEC)
50 poles
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
9.4 mm 0.370 in spacing
Blank card
Blank strip label
Blank marker
Universal wire markers holder

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Orange

JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50TP2
TP4
TC5
TC5-R1
VR-ZD
PT-ZD
MC512
MC512PA
MG-CPMFA 43196
MG-CPM 13 41790
UMH

1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900637R0000
1SNK900660R0000
1SNK140000R0000
1SNK149999R0000
1SNB043196R0012
1SNB041790R0512
1SNK900611R0000

50
50
50
50
30
10
20
20
10
10
50
50
22
20
400
1960
10

Dark grey
Dark greyBlack
Dark grey
White

Grey

1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.7
1.04
9.00
10.00
2.562
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 187

1SNK164032S0201

Accessories

CDK4 PI-Spring female plugs
Female plug - 6 mm 0.236 in spacing
Description

4 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDK4

1SNK160294V0014

1SNK160293V0014

10 AWG

CDK4-E

Ordering details
Description

Color

21.2 0.83"

36.3 1.43"

4
6 mm 0.236 in spacing

Part Number

CDK4
CDK4-E

1SNK806712R0000
1SNK806713R0000

IEC

UL - CSA

Rail

26 ... 10 AWG

Wire stripping
lengthFemale plugs
Female plugs without outer nubs - Closed

Grey

Main technical data

Pkg

Weightqty(1 pce) g

50
50

3.80
4.50

Mounting instructions

Connecting capacity

20.6 0.81"

Type

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 12 AWG
26 ... 12 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

30 A / 4 mm²
480 A

30 A / 10 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 VIP20600 V

12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

3

Locking devices
Cable Clamp
Terminal block
markersColor
9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part Number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41791 1SNB041791R0612
MG-CPMFA 43196 1SNB043196R0012
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1680
350
22
20
10

0.7
1.04
0.27
2.56
10.00
11.00
0.20

1SNK164006S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSScrew clamp Pluggable

PB-189

4

PAGE 189

ZDS4-22 Screw clamp pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
Description

4 mm²–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible for convenient
testing.
1SNK161137V0014

10 AWG

Ordering details
Description
Feed-through

Color

Type

4 connections

Grey

ZDS4-22Main technical data
ZDS4-2256.4 2.22"
48.9 1.93"
73 2.87"
65.5 2.58"

4
48.3 1.90"

5.2 mm 0.205 in spacing

1SNK805013R0000

Pkg

Weightqty(1 pce) g

50

10.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp
80.3 3.16"

Part Number

24 … 10 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
28 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDS4

CDS4-E

1 poleType
GreyPart Number

Pkg

Weightqty(1 pce) g

3.90
4.10

CDS4
CDS4-E

1SNK805714R0000
1SNK805715R0000

50
50

Type

Part Number

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
10
1960
22
20
10

14.00
1.85
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
3.57
0.23
9.00
10.00
0.20

15 poles max.

1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

10 mm
0.394 in
0.031 in
0.8 mm32 A (IEC)2 poles
32 A (IEC)3 poles
4 poles
32 A (IEC)
32 A (IEC)
5 poles
10 poles
32 A (IEC)
32 A (IEC)
50 polesCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAM4
1SNK900001R0000
EDS4-22
1SNK805911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164003S0201

Accessories

CDS4 Screw clamp female plugs
Female plug - 5.2 mm 0.205 in spacing
Description

4 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDS4

1SNK160296V0014

1SNK160295V0014

10 AWG

CDS4-E

Ordering details
Description

Color

Female plugs
Female plugs without outer nubs - Closed

Grey

24.3 0.96"

39.4 1.55"

5.2 mm 0.205 in spacing

Part Number

CDS4
CDS4-E

1SNK805714R0000
1SNK805715R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

3.90
4.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp

22.4 0.88"

Type

24 … 10 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
28 A / 10 AWG
Torque10.5 mm0.413 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

4

300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part Number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41790 1SNB041790R0512
MG-CPMFA 43196 1SNB043196R0012
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1960
350
22
20
10

0.7
1.04
0.23
2.56
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK164007S0201

3

Locking devices
Cable Clamp
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 191

ZDS4-22-R1 Screw clamp pluggable terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5-R1 + ES-TC6) withstanding 10 000 operations are compatible
for convenient testing.
1SNK161138V0014

10 AWG

Ordering details
Description
Feed-through

Color

Type

4 connections

Grey

ZDS4-22-R1

Main technical data
ZDS4-22-R1

73 2.87"
65.5 2.58"

56.4 2.22"
48.9 1.93"

4
48.3 1.90"

6 mm 0.236 in spacing

1SNK806013R0000

Pkg

Weightqty(1 pce) g

40

12.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp

80.3 3.16"

Part Number

24 … 10 AWG
24 … 10 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
28 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDS4-R1

CDS4-E

1 poleType
GreyPart Number

Pkg

Weightqty(1 pce) g

4.10
4.10

CDS4-R1
CDS4-E

1SNK806714R0000
1SNK805715R0000

50
50

Type

Part Number

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
20
20
20
10
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
3.57
0.27
10.00
11.00
0.20

15 poles max.

1

Description

2
1
2

3

4

5

6

7

8

3
4
5
6
7
8

Color

10 mm
0.394 in41 A (IEC)2 poles
41 A (IEC)3 poles
4 poles
41 A (IEC)
41 A (IEC)
5 poles
10 poles
41 A (IEC)
41 A (IEC)
50 polesCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 in
0.031 inSpacers
0.8 mmCoding pegs
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK164004S0201

Accessories

CDS4-R1 Screw clamp female plugs
Female plug - 6 mm 0.236 in spacing
Description

4 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDS4-R1

1SNK160296V0014

1SNK160297V0014

10 AWG

CDS4-E

Ordering details
Description

Color

Female plugs
Female plugs without outer nubs - Closed

Grey

24.3 0.96"

39.4 1.55"

6 mm 0.236 in spacing

Part Number

CDS4-R1
CDS4-E

1SNK806714R0000
1SNK805715R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

4.10
4.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp

22.4 0.88"

Type

24 … 10 AWG
24 … 10 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
28 A / 10 AWG
Torque10.5 mm0.413 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

4

300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part Number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41791 1SNB041791R0612
MG-CPMFA 43196 1SNB043196R0012
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1680
350
22
20
10

0.7
1.04
0.27
2.56
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK164008S0201

3

Locking devices
Cable Clamp
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 193

Summary_5

5INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, terminal block accessories

Common terminal block accessories				
Mounting railPR		

Screw end stops

BAM4, BAZH1

199

Screwless end stops

BAZ1		

200

Label holders

LH, LH-R1

201

Screwless jumper bars

196-198

LH-J			

202

JB5		

203

JB6		

204

JB8

205

JB10

206

JB12		207
Cross spacing jumpers

JB85-3		

208

Test adapters

TP2, TP4		

209

Test connectors

TC5		

210

Component plugs

PG5-R2		

211

PG5, PG5-R1

212

Screwdrivers

TO 		

213

Crimping tools

PS 		

213

PI-Spring terminal block accessories
End sections

EK		214-216

Circuit separators

CS-R2, CS-R3

Shield connectors

SHBP, SHB

217-218
219

Screw clamp terminal block accessories
End sections

ES		220-221

Screw jumper bars

JB8		

222

JB16, JB22

223		JB26			224

BJMI31, BJMI36

225

Lateral jumper bars

PC8, PC81		

226

Circuit separator

CS, CS-R1		

227

Shield connectors

SHBS, SHB

228

PL		

229

CO, KCO

230

Protecting covers
Short circuit bridges

SC-JB8231

Test sockets

AJS9		

232

5

Pluggable terminal block accessories
233-234

End sections

EDK, EDS		

Coding pegs

COP		

Locking devicesVR		235

Summary_5

235

PAGE 195PR mounting rail
Common terminal block accessories

1SNK500072F0000

Description–– Pre-punched symmetrical mounting rail,–– The slotted holes ease the mounting and allow to use existing and/or numerous fixings,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

Prepunched rail

PR30

1SNA173220R0500

Weight(1 pce) g2

328.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data

PR30

Zinc plating and passivation steel
TH 35-7.5

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

5

Description

1SNK500073F0000–– Symmetrical mounting rail complying with IEC60715,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

PR3.Z2

1SNA174300R1700

2

Weight(1 pce) g

718.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR3.Z2

Material
Rail

Zinc plating and passivation steel
TH 35-7.5

Equivalent E-Cu cross section

IEC
16 mm²

UL - CSA

All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).
1SNK160017S0201

2000 mm 78.74 in spacing

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPR mounting rail
Common terminal block accessories
Description

1SNK500073F0000–– Symmetrical mounting rail made of galvanised steel, complying with IEC60715,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

PR3.G2

1SNA164800R0300

2

Weight(1 pce) g

718.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR3.G2

Material
Rail

Galvanised steel
TH 35-7.5

Equivalent E-Cu cross section

IEC
16 mm²

UL - CSA

All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

5

Description

1SNK500074F0000–– Pre-punched symmetrical mounting rail,–– The slotted holes ease the mounting and allow to use existing and/or numerous fixings.

Ordering details
Description

Color

Preprunched rail

Type
PR50

Part Number
1SNA178529R0400

Pkg

Weightmeter(1 pce) g

21288.00

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR50

Zinc plating and passivation steel
TH 35-15

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions

1SNK160040S0201–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

2000 mm 78.74 in spacing

Technical data valid for copper conductors only.

PAGE 197

PR mounting rail
Common terminal block accessories
Description

1SNK500075F0000–– Symmetrical mounting rail.

Ordering details
Description

Color

Type
PR5

Part Number
1SNA168700R2200

Pkg

Weightmeter(1 pce) g

21200.00

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Zinc plating and passivation steel
TH 35-15

Material
Rail

PR5

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

2000 mm 78.74 in spacing

5

1SNK500076F0000

Description–– Symmetrical mounting rail complying with IEC60715,–– The rigidity of the rail is maximised by the 2.3 mm 0.090 in thickness of the rail, and by its solid, non slotted
construction,–– PR4 TH 35-15 is the most rigid mounting rail solution and it can suppo

Ordering details
Description

Color

Type

Part Number

Pkg
meter

Recommended for SNK ground terminal blocks up to
35 mm² 2 AWG
PR4

PR4

1SNA168500R1200

2

Weight(1 pce) g

915.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Material
Rail

Zinc plating and passivation steel
TH 35-15

Equivalent E-Cu cross section

IEC
50 mm²

UL - CSA
2 AWG

All the main technical data provided are "manufacturer" values.
RoHS

2000 mm 78.74 in spacing–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160041S0201

Mounting instructions

Screw end stops
Common terminal block accessories

1SNK160333V0014

BAM4 screw end stops
Description–– Give efficient support to the SNK terminal blocks assemblies thanks to the BAM4 double gripping rail contact,–– Ease the assemblies identification with the BAM4 marking location compatible with all SNK markers and labels.

Ordering details
Description

BAM4

Color

10 mm 0.394 in spacing

53.6 2.11"

Type

Dark grey

BAM4

36.2 1.42"

43.7 1.72"

Main technical data
Material specifications
Ambient temperature
min/max
26.8 1.06"

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900001R0000

Pkg

Weightqty(1 pce) g

50

14.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueTH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.9 Nm ± 0.1
7.08 lb.in ± 0.88

10 mm 0.394 in spacing

Mounting instructions

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Terminal block markers
Blank cardcompatible with MG3
In polycarbonate
In polyamide
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

White

Dark grey
Grey

Type

Part Number

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
LH
1SNK900605R0000
LH-R1
1SNK900607R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

1680
22
20
50
50
10

0.27
10.00
14.00
0.60
1.10
0.20

5

BAZH1 screw end stops
1SNK160094F0014

Description–– Give efficient support to the SNK double deck or power terminal blocks assemblies thanks to the BAZH1
double gripping rail contact,–– Ease the assemblies identification with label holders.

Ordering details
Description
BAZH1

Color

10 mm 0.394 in spacing

74.4 2.93"

Type

Dark grey

BAZH1

73.2 2.88"

65.7 2.59"

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900102R0000

Pkg

Weightqty(1 pce) g

20

24.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

TH 35-7.5
Flat screwdriverØ 5.5 mm
Ø 0.217 in

Torque1.3 Nm ± 0.1
11.4 lb.in ± 0.88

Part Number

Pkg

Weightqty(1 pce) g

1680
22
20
50
50
10

0.27
10.00
14.00
0.60
1.10
0.20

37.2 1.46"

10 mm 0.394 in spacing
All the main technical data provided are "manufacturer" values
RoHS

Description
Terminal block markers
Blank cardcompatible with MG3
In polycarbonate
In polyamide
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

Color
White

Dark grey
Grey

Type

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
LH
1SNK900605R0000
LH-R1
1SNK900607R0000
UMH
1SNK900611R0000

Technical data valid for copper conductors only.

PAGE 199

1SNK160026S0201

Accessories

Screwless end stops
Common terminal block accessories

BAZ1 screwless end stops
1SNK160247V0014

Description–– Reduce the size of your terminal block assemblies with the screwless reduced spacing BAZ1 end stop,–– Ease the assemblies identification with various markers and label holders.

Ordering details
Description

BAZ1

Color

5.2 mm 0.205 in spacing

53.5 2.11"

Type

Dark grey

BAZ1Main technical data
43.2 1.72"

35.7 1.43"

34.2 / 1.35"

Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900002R0000

Pkg

Weightqty(1 pce) g

50

5.30

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail

TH 35-7.5

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
50
50
10

0.23
9.00
10.00
0.60
1.10
0.20

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

24.2 0.95"

5.2 mm 0.205 in spacing

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

5compatible with MG3compatible with HTP500
compatible with AMS600
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

White

Dark grey
Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
LH
1SNK900605R0000
LH-R1
1SNK900607R0000
UMH
1SNK900611R0000

1SNK160002S0201

Terminal block markers
Blank card

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Label holder
Common terminal block accessories

1SNK160334V0014

LH label holder
Description–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Ordering details
Description
LH

Color

10 mm 0.394 in width

10 mm 0.394 in spacing

Type

Dark grey

LHPart Number

Pkg

Weightqty(1 pce) g

1SNK900605R0000

50

0.60

Part Number

Pkg

Weightqty(1 pce) g

25
25
25
10
1650
825
825
25

10.00
9.80
12.10
4.00
0.371
0.55
0.55
10.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

White
Self-adhesive precut blank label compatible with HTP500
White
Self-adhesive precut blank compatible with HTP500
label
Yellow
Pre-printed cover marker
Protection for RCPEAD markers Transparent
White
Precut blank label
compatible with MG3
Yellow
Self-adhesive precut blank compatible with MG3
label
White
Yellow
Self-adhesive precut blank label compatible with HTP500

Type
MCLH
RCPEAD-TT
RCPEAD-TT-YL
EPR2
MG-TAR 45490
MG-TAA 49448
MG-TAA 49498
MCLH-YL

1SNK900630R0000
1SNA235158R0100
1SNA235159R0200
1SNA399726R0700
1SNB045490R8530
1SNB049448R8530
1SNB049498R8530
1SNK900633R0000

5

1SNK160335V0014

LH-R1 label holder
Description–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Ordering details
19.5 mm 0.768 in spacing

Mounting instructions

Description

Color

19.5 mm 0.768 in widthType

Dark grey

LH-R1

Part Number

Pkg

Weightqty(1 pce) g

1SNK900607R0000

50

1.10

Part Number

Pkg

Weightqty(1 pce) g

25
1
1
25
25
900
450
450
25

10.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Self-adhesive precut blank label compatible with HTP500
Precut blank label
compatible with AMS600
Protection for RCPEB markers
Self-adhesive precut blank compatible with HTP500
label
Precut blank label
compatible with MG3
Self-adhesive precut blanklabel
Self-adhesive precut blank label compatible with HTP500

Color
White
White
Transparent
White
YellowWhite
YellowWhite
YellowType
MCLH-R1
RCPEB
EPR1
PIB2-TT
PIB2-TT-YL
MG-TAR 45194
MG-TAA 49148
MG-TAA 49198
MCLH-R1-YL

1SNK900631R0000
1SNA178430R0500
1SNA178431R2200
1SNA235155R2600
1SNA235157R2000
1SNB045194R1735
1SNB049148R1735
1SNB049198R1735
1SNK900634R0000

0.05
9.70
9.40
0.62
0.91
0.91
10.00

Technical data valid for copper conductors only.

PAGE 201

1SNK160023S0201

LH

Label holder
Common terminal block accessories

1SNK160347V0014

LH-J label holder
Description
Easily identify your block with three standard 5.2 mm 0.205 in spacing SNK markers. It fits in the jumper
channel of the SNK terminal blocks.

LH

Ordering details

4.8 mm 0.189 in spacing

87 3.4"94.5 3.7"

Description

Color

Rotating label holder with three SNK markers housings- 4.8 mm 0.189 in spacing

Dark grey

LH-J

Part Number

Pkg

Weightqty(1 pce) g

1SNK900606R0000

100

0.73

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications

44.9 1.73"

Type

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Blank marker
Blank cardcompatible with MG3compatible with HTP500
compatible with AMS600
Universal wire markers holder 5.2 mm 0.205 in spacing

Color
White
White
White
Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

1SNK160096S0201

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSJB5 screwless jumper bars
Common terminal block accessories

1SNK160143F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
5.2 mm 0.205 in spacing

Color

5.2 mm 0.205 in spacing

2 poles
3 poles
4 poles
5 poles
10 poles
50 polesOrangeType

Pkg

Part Number

JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50

1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000

Weightqty(1 pce) g

50
50
50
50
30
10

1.30
2.00
2.70
3.50
7.10
36.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
32 A
1000 V
800 V
630 V
400 V
400 V

UL - CSA
30 A
600 V
300 V
300 V
150 V
150 V

8000 V
IP20

NEMA 1Ex e
Pleaseconsultus
5

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.
15 poles max. recommended for convenient mounting.
3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
For all other applications, please consult us.

Technical data valid for copper conductors only.

PAGE 203

1SNK160027S0201

JB5

JB6 screwless jumper bars
Common terminal block accessories

1SNK160143F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
JB6
6 mm 0.236 in spacingColor

6 mm 0.236 in spacing

2 poles
3 poles
4 poles
5 poles
10 poles
50 polesOrangeType

Pkg

Part Number

JB6-2
JB6-3
JB6-4
JB6-5
JB6-10JB6-50

1SNK906302R0000
1SNK906303R0000
1SNK906304R0000
1SNK906305R0000
1SNK906310R0000
1SNK906350R0000

Weightqty(1 pce) g

50
50
50
50
20
10

1.30
2.10
2.90
3.60
7.40
38.10

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
41 A
1000 V
800 V
630 V
400 V
400 V

UL - CSA
30 A
600 V
300 V
300 V
150 V
150 V

8000 V
IP20

NEMA 1Ex e
Please consult
our dedicatedcertificates

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.
15 poles max. recommended for convenient mounting.
3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
For all other applications, please consult us.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160029S0201

5

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

JB8 screwless jumper bars
Common terminal block accessories

1SNK160146F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
8 mm 0.315 in spacingColor

8 mm 0.315 in spacing

2 poles
3 poles
4 poles
5 poles
10 polesOrangeType

Pkg

Part Number

JB8-2
JB8-3
JB8-4
JB8-5
JB8-10

1SNK908302R0000
1SNK908303R0000
1SNK908304R0000
1SNK908305R0000
1SNK908310R0000

Weightqty(1 pce) g

50
50
50
40
20

2.70
4.10
5.60
7.00
14.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
57 A
1000 V
800 V
630 V
630 V
630 V

UL - CSA
42 A
600 V
300 V
300 V
150 V
150 V

6000 V
IP20

Ex e
693 V
440 V
440 V
352 V
352 V
5

NEMA 1

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.
3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
1SNK160030S0201

JB8

For all other applications, please consult us.

Technical data valid for copper conductors only.

PAGE 205

JB10 screwless jumper bars
Common terminal block accessories

1SNK160146F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
JB10
10 mm 0.394 in spacingColor

10 mm 0.394 in spacing

2 poles
3 poles
4 poles
5 poles
10 polesOrangeType

Pkg

Part Number

JB10-2
JB10-3
JB10-4
JB10-5
JB10-10

1SNK910302R0000
1SNK910303R0000
1SNK910304R0000
1SNK910305R0000
1SNK910310R0000

Weightqty(1 pce) g

50
50
40
30
20

4.60
7.10
9.40
12.00
24.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
76 A
1000 V
800 V
630 V
400 V
250 V

UL - CSA
67 A
600 V
300 V
300 V
150 V
150 V

6000 V
IP20

NEMA 1

Ex e
693 V
440 V
440 V
275 V
176 V

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.
3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
For all other applications, please consult us.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK160031S0201

5

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

JB12 screwless jumper bars
Common terminal block accessories

1SNK160239V0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
12 mm 0.472 in spacingColor

12 mm 0.472 in spacing

2 poles
3 poles
5 polesOrangeType

Pkg

Part Number

JB12-2
JB12-3
JB12-5

1SNK912302R0000
1SNK912303R0000
1SNK912305R0000

Weightqty(1 pce) g

50
50
20

4.90
7.60
12.90

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
76 A
1000 V
800 V
630 V
320 V
250 V

UL - CSA
67 A
600 V
300 V
300 V
150 V
150 V

6000 V
IP20

NEMA 1

Ex e
693 V
440 V
440 V
220 V
176 V

5

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.
3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
1SNK160071S0201

JB12

For all other applications, please consult us.

Technical data valid for copper conductors only.

PAGE 207

JB85-3 cross spacing jumpers
Common terminal block accessories

1SNK160125F0014

Description–– Allows power distribution between terminal blocks with different spacing,–– JB5-3, JB6-3 and JB8-3 can be used as cross spacing jumpers (see selection table on mounting instructions below).

Ordering details
Description

Color

Cross spacing jumpers

3 polesType

OrangePart Number

JB85-3

1SNK900603R0000

Pkg

Weightqty(1 pce) g

10

2.80

Main technical data
JB85

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Material specifications

8 mm 0.315 in spacing

Ambient temperature
min/max

Rated current
Rated voltage

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
32 A
1000 V
800 V
630 V
8000 V
IP20

Standard use
Cut extremities
Cut poles

Impulse withstand voltage
Protection-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA
30 A
600 V
300 V
300 V

Ex e
Please consult
our dedicatedcertificates

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

Mounting instructions
Cross spacing jumper selection between A and B terminal blocks with different
spacing.

5

B 5.2 mm

6 mm

8 mm

JB85.3
JB85.3
JB6.3

JB8.3
-

A
6 mm
8 mm
10 mm
12 mm

JB5.3
JB85.3
JB85.3
JB85.3I1 maxBlue cell: for ZS terminal blocks only

I1 max + I2 max ≤ I max		
		
I max		I1 max≤ I rated terminal blockI2 max		

1SNK160054S0201

I max

I2 maxYellow cell: for ZS and ZK terminal blocks

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSTest adapters
Common terminal block accessories

TP2 test adapters
1SNK160093V0014

Description–– Insulated test adapter that enables individual voltage control,–– Direct plug-in solution into the jumpers channels,–– Compatible with standard isolated or non isolated test plugs DIA 2 mm 0.079 in and 2.3 mm 0.090 in,–– Withstand more than 10000 operations according to TE Connectivity test standards.

Ordering details

TP

Description

7.6 mm 0.299 in spacing

Color

For test plugs DIA 2 mm 0.079 inMounting instructions

TP2

Part Number
1SNK900203R0000

Pkg

Weightqty(1 pce) g

20

1.70

Main technical data
Material specifications
Ambient temperature
min/max✔

Dark grey

Type

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Standard use
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
10 A
1000 V
8000 VIP20-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA

Ex e

600 V

Not authorized

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

5

TP4 test adapters
1SNK160093V0014

Description–– Isolated test adapter that enables individual voltage control,–– Direct plug-in solution into the jumpers channels,–– Compatible with standard insulated or non isolated test plugs DIA 4 mm 0.157 in,–– Withstand more than 10000 operations according to TE Connectivity test standards.

Ordering details

TP

Description

7.6 mm 0.299 in spacing

Color

For test plugs DIA 4 mm 0.157 inMounting instructions

TP4

Part Number
1SNK900205R0000

Pkg

Weightqty(1 pce) g

20

2.40

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Standard use
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
16 A
1000 V
8000 VIP20-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA

Ex e

600 V

Not authorized

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

1SNK160036S0201✔

Dark grey

TypeTechnical data valid for copper conductors only.

PAGE 209

TC5 test connectors
Common terminal block accessories
Description
Ease the testing of terminal block assemblies:–– Make your own test connector assembly with our modular solution mixing various spacings,–– Direct plug-in solution into the jumpers channels,–– Withstand more than 10000 operations according to TE Connectivity test standards.
ES-TC6

ES-TC8Main technical data
IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 1.5 mm²0.22 ... 1.5 mm²

1 conductor
per clamp

TC5-R1TC5

5.2 mm 0.205 in spacing

TC5-R1
TC5

Mounting instructions

Connecting capacity

UL - CSA

0.22 ... 1.5 mm²A1-B1
0.2 ... 0.75 mm²0.22 ... 0.75 mm²0.22 ... 0.75 mm²
16 A / 1.5 mm²
180 A1000 V
8000 V
IP20

RailWire stripping
lengthTool

Torque8 mm
0.314 inFlat screwdriverØ 2.5 mm
Ø 0.098 in

0.5 Nm ± 0.1
3.43 lb.in ± 0.885

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

Material specifications
Ambient temperature
min/max
10 poles max.

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values

5

RoHS

TC5-R1

Ordering details

ES-TC6

Test connectors for 5.2 mm 0.205 in spacing terminal blocks
Description

Color

Test connectors 5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey

Part Number

TC5
TC5-R1

1SNK900200R0000
1SNK900201R0000

TypePart Number

Pkg

Weightqty(1 pce) g

10
10

5.20
5.20

Ordering details

10 poles max.

Test connectors for 6 mm 0.236 in spacing terminal blocks
Description

TC5-R1

TypeTC5ES-TC8Color

Test connectors End module, 5.2 mm 0.205 inSpacers
0.8 mm 0.031 in spacing

Dark grey

TC5-R1
ES-TC6

1SNK900201R0000
1SNK900105R0000

TypePart Number

Pkg

Weightqty(1 pce) g

10
10

5.20
0.80

Ordering details
Test connectors for 8 mm 0.315 in spacing terminal blocks
Description

10 poles max.

Color

Test connectors 5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 inSpacers
2.8 mm 0.110 in spacing

Pkg

Weightqty(1 pce) g

5.20
5.20
1.40

Dark grey

TC5
TC5-R1
ES-TC8

1SNK900200R0000
1SNK900201R0000
1SNK900104R0000

10
10
10

Color

Type

Part Number

Pkg

Weightqty(1 pce) g

20
1960
22
20
10

1.00
0.23
9.00
10.00
0.20

Description

PT-3

Cable clamps
Terminal block
markers

Fit on two C2.5-ZDP plugs and on TC5 test connectors
Blank marker
Blank card
Universal wire markers holder

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Dark grey
White

Grey

PT-3
1SNK900625R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

1SNK160042S0201

Accessories

Component plugs
Common terminal block accessories

PG5-R2 component plugs
Description
48.9 1.92"

27.8 1.09"

1SNK160112F0014

37.7 1.48"

18.9 .74"–– Component holder compatible with 5.2 mm 0.205 in spacing ZS4 feed-through terminal blocks,–– Fit components 16 x 16 x 8.5 mm 0.630 x 0.630 x 0.335 in (not supplied with plug) such as resistors, diodes, varistance,–– Direct plug-in into the terminal blocks jumper channels,–– Maximum dissipatived power: 2 W.

PG5
9.95 mm 0.392 in spacing

Ordering details
Description

Mounting instructions

Color

Components insertion between 2 blocks

Type

Dark grey

PG5-R2

Part Number

Pkg

Weightqty(1 pce) g

1SNK900403R0000

20

8.00

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC

UL - CSA

250 V
4000 V
IP20

NEMA 1

All the main technical data provided are "manufacturer" values–– Open the PG5-R2 with a flat screw-

RoHS

Accessories
Description
Terminal block markers
Blank card
Universal wire markers holder

Color
White

In polycarbonate
Blank card
5.2 mm 0.205 in spacing

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

5

1SNK160039S0201

driver DIA . 3.5 mm 0.138 in,–– Use a soldering iron to fix your component,–– Close the PG5-R2,–– Plug-in in the terminal blocks jumper
channels.

Technical data valid for copper conductors only.

PAGE 211

Component plugs
Common terminal block accessories

PG5 component plugs
Description
39 1.54"24.6 .97"

1SNK160022F0014

31 1.22"

17 .67"–– Ease the components installation ( components not supplied with plug ) with our quick plug-in mounting
system which avoids soldering process,–– Accept 8.8 x 3.2 mm 0.346 x 0.125 in components such as resistors, diodes or subminiature fuses (fully
encapsulated),–– Maximum dissipatived power: 1 W.

PG5Ordering details

5.2 mm 0.205 in spacing

Description

Color

Components in series with circuit

Mounting instructions

Type

Dark grey

PG5

Part Number

Pkg

Weightqty(1 pce) g

1SNK900401R0000

20

3.50

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Impulse withstand voltage
Protection–– Direct plug-in in disconnect withplug terminal block

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC

UL - CSA

400 V
6000 V
IP20

150 V
NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Terminal block markers
Blank card

5

White

In polycarbonate
Blank card
5.2 mm 0.205 in spacing

Universal wire markers holder

Description
39 1.54"24.6 .97"

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

PG5-R1 disconnect plugs

31 1.22"

1SNK160120F0014

Grey

Type

Allow disconnect function when associated with the disconnect with plug terminal blocks.

Ordering details
Description

Color

Type

Part Number

Equipped with linking bar

OrangePG5Main technical data

5.2 mm 0.205 in spacing

Material specifications

Mounting instructions

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
18 A
400 V
6000 V
IP20

Rated current
Rated voltage
Impulse withstand voltage
Protection

PG5-R1

Pkg

Weightqty(1 pce) g

1SNK900402R0000

20

3.50

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

17 .67"-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA
20 A
150 V
NEMA 1

All the main technical data provided are "manufacturer" values
RoHS–– PG5-R1 totally inserted: closed circuit,–– PG5-R1 inserted in central position:
open circuit, plug secured in isolated
central position

Description
Terminal block markers
Blank card
Universal wire markers holder

Color
White

In polycarbonate
Blank card
5.2 mm 0.205 in spacing

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

1SNK160037S0201

Accessories

ToolsCommon terminal block accessories

TO screwdrivers
1SNK160242F0014

Description
Flat head screwdriver

Ordering details
Description

Color

Insulated screwdriver 1000V IEC dimensions 3.5 x
100 mm 0.138 x 3.94 inscrewdriver 3.5 x 50 mm 0.138 x 1.97 inscrewdriver 3.5 x 50 mm 0.138 x 1.97 in Angled 60°
screwdriver 4 x 100 mm 0.157 x 3.94 inscrewdriver 5.5 x 125 mm 0.216 x 4.92 inscrewdriver 6.5 x 150 mm 0.256 x 5.90 in

TO

Type

Part Number

Pkg

Weightqty(1 pce) g

TO3.5-100-INS

1SNK900644R0000

1

37.00

TO3.5-50
TO3.5-50-A
TO4-100
TO5.5-125
TO6.5-150

1SNK900640R0000
1SNK900659R0000
1SNK900641R0000
1SNK900642R0000
1SNK900643R0000

12
12
1
1
1

22.00
21.6
42.00
75.50
121.00PS

PS crimping tools
Description–– Crimp flexible conductors equipped with ferrules from 0.08 to 10 mm² 28 AWG to 7 AWG,–– Semi-automatic crimping tool.

Ordering details
Description
180 mm 7.09 in length

Color

Type
PS-3

Part Number
1SNK900650R0000

Pkg

Weightqty(1 pce) g1

380.00

1SNK160028S0201

1SNK160127F0014

5

Technical data valid for copper conductors only.

PAGE 213

End sections
PI-Spring terminal block accessories

EK2.5 end sections
1SNK160233V0014

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5, ZK2.5-PE, ZK4, ZK4-PE, ZK6 and ZK6-PE PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

EK2.5

Dark grey

Type
EK2.5

Part Number
1SNK705910R0000

Pkg

Weightqty(1 pce) g

20

1.80

1SNK160234V0014

EK2.5-3P end sections
Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5-3P, ZK2.5-PE-3P, ZK4-3P, ZK4-PE-3P, ZK2.5-S..., ZK2.5-SP and ZK2.5-SF... PISpring screwless terminal blocks.

Ordering details
EK2.5-3P

Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-3PPart Number
1SNK705911R0000

Pkg

Weightqty(1 pce) g

20

2.40

EK2.5-4P end sections
1SNK160235V0014

5

EK2.5-4P

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5-4P, ZK2.5-PE-4P, ZK4-4P and ZK4-PE-4P PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-4P

Part Number
1SNK705912R0000

Pkg

Weightqty(1 pce) g

20

2.70

Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160064S0201

Main technical data

End sections
PI-Spring terminal block accessories

1SNK160339V0014

EK2.5-S-4P end sections
Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5-S-4P, ZK2.5-SP-4P, ZK2.5-CH-4P... PI-Spring screwless terminal blocks.

Ordering details

EK2.5-S-4P

Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-S-4PPart Number
1SNK705913R0000

Pkg

Weightqty(1 pce) g

20

2.94

EK2.5-D2 end sections
1SNK160237V0014

Description–– Compatible with ZK2.5-D2, ZK2.5-D2-PE, ZK2.5-D1 and ZK2.5-D1-PE PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-D2

Part Number
1SNK705960R0000

Pkg

Weightqty(1 pce) g

20

3.40

EK2.5-D2

EK2.5-T3 end sections

5

1SNK160346V0014

Description–– Compatible with ZK2.5-T3, ZK2.5-T1, ZK2.5-T1-PE, ZK2.5-L-L-PE and ZK2.5-L-N-PE PI-Spring screwless
terminal blocks.

Ordering details
Description

Color

0.8 mm 0.031 in spacing

Dark grey

Type
EK2.5-T3

Part Number
1SNK705961R0000

Pkg

Weightqty(1 pce) g

20

4.76

EK2.5-T3

Main technical data

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160065S0201

Material specifications

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 215

End sections
PI-Spring terminal block accessories

1SNK160236V0014

EK6-3P end sections
Description–– Compatible with ZK6-3P and ZK6-PE-3P PI-Spring screwless terminal blocks.

Ordering details
Description

EK6-3PColor

2 mm 0.079 in spacing

Dark grey

Type
EK6-3PPart Number
1SNK708911R0000

Pkg

Weightqty(1 pce) g

20

2.80

1SNK160238V0014

EK10 end sections
Description–– Compatible with ZK10, ZK10-PE, ZK16 and ZK16-PE PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK10

Part Number
1SNK710910R0000

Pkg

Weightqty(1 pce) g

20

3.30

EK10

1SNK160318V0014

EK10-3P end sections
5

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK10-3P, ZK10-PE-3P, ZK16-3P, ZK16-PE-3P... PI-Spring screwless terminal blocks.

Ordering details
EK10-3P

Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK10-3P

Part Number
1SNK710911R0000

Pkg

Weightqty(1 pce) g

20

4.5

Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160095S0201

Main technical dataCircuit separators
PI-Spring terminal blocks accessories

CS-R2 circuit separators
1SNK160240V0014

Description–– Compact circuits separator solution (only 3mm spacing) which provides a convenient visual identification of
the several circuits within terminal assemblies,–– Unique top marking possibility that can replace the conventional solution of "end stop with label holder"for demanding applications with high space constraints, - Compatible with all PI-spring feed-through andground terminal blocks up to 8 mm spacing,–– Mounting on DIN3-TH35 rail.

Ordering details
Description

CS-R2
61.8 2.67"

Color

3 mm 0.118 in spacing

Type

Dark grey

CS-R2

Part Number

Pkg

Weightqty(1 pce) g

1SNK900106R0000

20

3.80

Part Number

Pkg

Weightqty(1 pce) g

1680
5250
5250
22
20
10

0.27
0.04
0.05
10.00
11.00
0.20

48.7 1.92"

Main technical data
Material specifications
Ambient temperature
min/max

3 mm 0.118 in spacing

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Terminal block markers
LabelsColor
White
Yellow
White

In polycarbonate
Blank card
Universal wire markers holder 5.2 mm 0.205 in spacing

White
Grey

MG-CPM 13 41791 1SNB041791R0612
MG-VYT 46415
1SNB046415R0615
MG-VYT 46915
1SNB046915R0615
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

5

1SNK160072S0201

Blank card

TypeTechnical data valid for copper conductors only.

PAGE 217

Circuit separators
PI-Spring terminal blocks accessories

1SNK160241V0014

CS-R3 circuit separators

CS-R3
98.8 3.89"

Description–– Compact circuits separator solution (only 3mm spacing) which provides a convenient visual identification of
the several circuits within terminal assemblies,–– Unique top marking possibility that can replace the conventional solution of "end stop with label holder" fordemanding applications with high space constraints,–– Compatible with all single deck PI-spring terminal blocks and ZS10-ST...terminal blocks ,–– Mounting on DIN3-TH35 rail.

Ordering details
53.7 2.11"

Description

3 mm 0.118 in spacingColor

3 mm 0.118 in spacing

Type

Dark grey

CS-R3

Part Number

Pkg

Weightqty(1 pce) g

1SNK900107R0000

20

6.40

Part Number

Pkg

Weightqty(1 pce) g

1960
1680
5250
5250
22
20
22
20
10

0.23
0.27
0.04
0.05
9.00
10.00
10.00
11.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Terminal block markers

White

LabelsYellow
White

Blank card

In polycarbonate
Blank card
In polycarbonate
Blank card
Universal wire markers holder 5.2 mm 0.205 in spacing

White

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MG-CPM 13 41791 1SNB041791R0612
MG-VYT 46415
1SNB046415R0615
MG-VYT 46915
1SNB046915R0615
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

1SNK160098S0201

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS1SNK160267F0014

Shield connectors
PI-Spring terminal block accessories

SHBP/SHBSHBP/SHB shield connectors for PI-Spring terminal blocks
Description–– Ensure the continuity of your shield connection,–– Various connection solutions available: RILS cable ties, soldering, quick-connect.

Ordering details
13.67 .54"

Description
128 5.04"
SHB

Color

Compatible with ZK2.5 and ZK2.5-S terminal blocks
Compatible with ZS and ZK double deck terminal blocks

Type
SHBP
SHB

Part Number
1SNK900601R0000
1SNK900602R0000

Pkg

Weightqty(1 pce) g

20
20

4.10
4.90

SHBP

12.2 0.48"

Main technical data
Material specifications
Ambient temperature
min/max

116 4.57"

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

SHBP
Rated voltage-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
100 V

UL - CSA

Ex e
50 V

All the main technical data provided are "manufacturer" values
RoHS

Accessories for screw clamp and PI-Spring terminal blocks
Description
Cable ties

Color
For SNK shield connector

Type
RILS

Part Number
1SNK900627R0000

Pkg

Weightqty(1 pce) g

10

0.30

5

Mounting instructions–– SHBS is directly fixed on the terminal block,–– SHB is fixed on the ES4-D2 end section,–– SHBP is directly fixed on the terminal block,–– Connect the cable shielding on the shielding connector with:–– RILS cable ties,–– quick-connect (the shield connector needs to beprepared),

1SNK160044S0201–– soldering iron.

Technical data valid for copper conductors only.

PAGE 219

End sections
Screw clamp terminal block accessories

ES4 end sections
1SNK161013F0014

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with feed-through, ground and disconnect screw clamp terminal blocks.

Ordering details
Description

Color

2.2 mm 0.087 in spacing

Dark grey

Type
ES4

Part Number
1SNK505910R0000

Pkg

Weightqty(1 pce) g

20

2.20

ES4

ES6-3S end sections
1SNK160229V0014

Description–– Compatible with ZS6-3S and ZS6-3S-PE terminal blocks.

Ordering details
Description

Color

2.2 mm 0.087 in spacing

Dark greyTypeES6-3SPart Number
1SNK505912R0000

Pkg

Weightqty(1 pce) g

20

2.50

ES6-3S

1SNK160230V0014

ES6-4S end sections
5

Description–– Compatible with ZS6-4S, ZS6-4S-PE, ZS6-S-4S-T2 and ZS4-PE-R2 terminal blocks.

Ordering details
Description

Color

2.2 mm 0.087 in spacing

ES6-4S

Dark greyTypeES6-4SPart Number
1SNK505911R0000

Pkg

Weightqty(1 pce) g

20

3.10

ES4-D2 end sections
1SNK161012F0014

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with double deck screw clamp terminal blocks

Ordering details
Description

Color

2.55 mm 0.100 in spacing

Dark grey

Type
ES4-D2

Part Number
1SNK505960R0000

Pkg

Weightqty(1 pce) g

20

4.10

ES4-D2

Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160061S0201

Main technical data

End sections
Screw clamp terminal block accessories

ES4-T3 end sections
Description
1SNK160232V0014–– Compatible with ZS4-T3 terminal block.

Ordering details
Description

Color

0.8 mm 0.031 in spacing

Type

Dark grey

ES4-T3

Part Number
1SNK505961R0000

Pkg

Weightqty(1 pce) g

20

4.20

ES4-T3

ES4-SF end sections
1SNK161026F0014

Description–– Compatible with fuse ZS4-SF1... and disconnect screw clamp terminal blocks ZS4-S-R3.

Ordering details
Description

Color

1.5 mm 0.059 in spacing

Type

Dark grey

Part Number

ES4-SF

1SNK508960R0000

TypePart Number

Pkg

Weightqty(1 pce) g

20

1.80

ES4-SF

ES4-D2-SF1 end sections
Description
1SNK160231V0014–– Compatible with ZS4-D2-SF1 ... terminal blocks.

Ordering details
Description

Color

2.5 mm 0.098 in spacing

Dark grey

ES4-D2-SF1

1SNK508911R0000

Pkg

Weightqty(1 pce) g

20

5.00

5

ES4-D2-SF1

1SNK161072F0014

ES10-ST end sections
Description–– Unique dark grey color that fits all test disconnect terminal blocks ZS10-ST... and ease the identification of
circuits within your terminal block assemblies,–– Also compatible with ZS10-R1 and ZS10-PE-R1.

Ordering details
Description

Color

2 mm 0.079 in spacing

TypePart Number

Pkg

Weightqty(1 pce) g

3.5

Dark grey

ES10-ST

1SNK508910R0000

20

Color

Type

Part Number

Pkg

Weightqty(1 pce) g

20

0.20

Accessories
Description
Circuit separators

0 mm 0 in spacing

Dark greyCS

1SNK900101R0000

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160062S0201

ES10-ST

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 221

Screw jumper bars
Screw clamp terminal block accessories

JB8 jumper bars
Description
1SNK160212F0014

Insulated jumper bar with screw mounting.

Ordering details
Description

Color

8 mm 0.315 in spacing

JB8
8 mm 0.315 in spacing

Orange

JB8-2-R1
JB8-3-R1
JB8-4-R1
JB8-5-R1
JB8-10-R1

Part Number
1SNK908902R0000
1SNK908903R0000
1SNK908904R0000
1SNK908905R0000
1SNK908910R0000

Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Standard use

IEC
50 A
160 V

a

Rated current
Rated voltage
b

10
10
10
10
10

7.6
11.6
15.5
19.4
39.00

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueUL - CSA
51 A

Alternated poles
Impulse withstand voltage
Protection

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.7 Nm ± 0.1
6.2 lb.in ± 0.88

Ex e

Not authorized
IP20

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

1SNK161061S0201

5

1 - Rated voltage: 160 V (IEC) / Not
authorized (UL)
2 - Rated voltage: 320 V (IEC) / Not
authorized (UL)
3 - Rated voltage: 1000 V (IEC) / 300
V (UL)
a - End section ES10-ST
b - End stop BAZ1

Weight(1 pce) g

Rail

2

3

Pkg
qty

Main technical data

Mounting instructions
1

2 poles
3 poles
4 poles
5 poles
10 poles

Type

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSScrew jumper bars
Screw clamp terminal block accessories

JB16 jumper bars
Description
1SNK160124F0014

Insulated jumper bar with screw mounting.

Ordering details
Description

Color

16 mm 0.630 in spacing

JB16
16 mm 0.630 in spacing

2 poles
3 poles
4 poles
5 poles
10 polesOrangeType
JB16-2
JB16-3
JB16-4
JB16-5
JB16-10

Part Number
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK916310R0000

Pkg

Weightqty(1 pce) g

10
10
10
10
10

10.00
16.00
22.00
28.00
56.60

Main technical data
Material specifications

Mounting instructions
Ambient temperature
min/max

Rated current
Rated voltage–– With flat pliers, cut out the partitions

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
125 A
1000 VUL - CSA
150 A
600 V

Rail

Alternated poles

TorqueFlat screwdriverØ 5.5 mm
Ø 0.217 in

1.2 Nm ± 0.1
10.6 lb.in ± 0.885

Ex e

Not authorized
8000 V
IP20

Impulse withstand voltage
Protection

Tool

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

5

Description
Screw jumper bars

Ordering details
Description

JB22

Color

22 mm 0.866 in spacing

22 mm 0.866 in spacing

Mounting instructions

Ambient temperature
min/max

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

JB22-2
JB22-3
JB22-5
JB22-10

Part Number
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK922310R0000

Pkg

Weightqty(1 pce) g

5
5
5
5

27.00
43.30
76.10
157.40Main technical data
Material specifications–– With flat pliers, cut out the partitions

2 poles
3 poles
5 poles
10 polesType

Rated current
Rated voltage

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
192 A
1000 VUL - CSA
175 A
600 V

Alternated poles
Impulse withstand voltage
Protection

Rail
Tool
TorqueAllen keyØ 4 mmØ 0.157 in

2 Nm ± 0.4
17.7 lb.in ± 3.54

Ex e
630 V
Not authorized

8000 VIP20

1SNK160032S0201

1SNK160100F0014

JB22 jumper bars

All the main technical data provided are "manufacturer" values
RoHS

Technical data valid for copper conductors only.

PAGE 223

Screw jumper bars
Screw clamp terminal block accessories

1SNK160100F0014

JB26 jumper bars
Description
Screw jumper bars

Ordering details
Description

JB26

Color

26 mm 1.02 in spacing

26 mm 1.024 in spacing

Mounting instructions

Ambient temperature
min/max

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

JB26-2
JB26-3
JB26-5
JB26-10

Part Number
1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK926310R0000

Pkg

Weightqty(1 pce) g

5
5
5
5

41.20
65.70
115.70241.50Main technical data
Material specifications–– With flat pliers, cut out the partitions

2 poles
3 poles
5 poles
10 polesType

Rated current
Rated voltage

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
232 A
1000 VUL - CSA
230 A
600 V

Rail

Alternated poles
Impulse withstand voltage
Protection

Tool
TorqueAllen keyØ 4 mmØ 0.157 in

2 Nm ± 0.4
17.7 lb.in ± 3.54

Ex e
630 V
Not authorized

8000 V
IP20

All the main technical data provided are "manufacturer" values
RoHS

1SNK160034S0201

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSScrew jumper bars
Screw clamp terminal block accessories

1SNK160100F0014

BJMI31 jumper bars
Description
Screw jumper bars

Ordering details
Description

Color

31mm 1.220 in spacing

BJMI3131 mm 1.22 in spacing

2 poles
3 polesType
BJMI31.2
BJMI31.3

Part Number
1SNA206053R0700
1SNA206054R0000

Pkg

Weightqty(1 pce) g

1
1120.00190.00Main technical data
Material specifications

Mounting instructions

Ambient temperature
min/max

Rated current
Rated voltage–– With flat pliers, cut out the partitions

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
309 A
1000 VUL - CSA
445 A
600 V

Rail

Alternated poles

Tool
TorqueAllen keyØ 5 mmØ 0.196 in

3 Nm ± 0.4
26.55 lb.in ± 3.54

Ex e

Not authorized
8000 V
IP20

Impulse withstand voltage
Protection
All the main technical data provided are "manufacturer" values
RoHS

5

Description
Screw jumper bars

Ordering details
Description

BJMI3636 mm 1.42 in spacing

Mounting instructions

Color

36mm 1.41i7 n spacing

Material specifications

Rated current
Rated voltage

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

BJMI36.2
BJMI36.3

Part Number
1SNA206126R2500
1SNA206223R0600

Pkg

Weightqty(1 pce) g1
1

170.00260.00Main technical data

Ambient temperature
min/max–– With flat pliers, cut out the partitions

2 poles
3 polesType

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
415 A
1000 VUL - CSA
620 A
600 V

Rail

Alternated poles
Impulse withstand voltage
Protection

Tool
TorqueAllen keyØ 5 mmØ 0.196 in

3 Nm ± 0.4
26.55 lb.in ± 3.54

Ex e

Not authorized
8000 V
IP20

All the main technical data provided are "manufacturer" values

1SNK160097S0201

1SNK160100F0014

BJMI36 jumper bars

RoHS

Technical data valid for copper conductors only.

PAGE 225

1SNC160112F0014

Lateral jumper bars
Screw clamp terminal block accessories

PC8
8 mm 0.315 in spacing

PC8 lateral jumper bars
Description
IP20 Comb jumper bars,–– direct insertion in the screw clamp before tightening the screws, above the eventual conductor (if conductorused with ferrule, we recommend the use of long ferrule for optimized mounting ergonomy with test disconnect terminal blocks),–– Multiple versions available in pre-cut poles for test disconnect terminal blocks applications.

Ordering details

Mounting instructions for
ZS10-ST...

Description

Color

Lateral jumper bars
8 mm 0.315 in 2 poles
spacing
3 poles
4 poles
10 poles1a2b

1 - Rated voltage: 630 V (IEC) / 150 V (UL)
2 - Rated voltage: 630 V (IEC) / 300 V (UL)a - End section ES10-ST
b - End stop BAZ1

Lateral jumper bars pre-cut poles
8 mm 0.315 in 4/6 poles
spacing
4/8 poles
4/10 poles
3/4 poles
4/7 poles
2/3 poles
4/6 poles
4/8 poles

Type

Part Number

Pkg

Weightqty(1 pce) g

Black

PC8-2
PC8-3
PC8-4
PC8-10

1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400

10
10
10
10

3.00
4.00
6.00
14.00

Black

PC8-R1
PC8-R2
PC8-R3
PC8-R4
PC8-R5
PC8-R6
PC8-R7PC8-R8

1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400842R0000
1SNA400843R0000
1SNA400849R0000
1SNA400850R0000

10
10
10
10
10
10
10
10

6.60
7.80
9.00
4.50
6.60
6.60
6.60
7.80

Main technical data
Material specifications
Ambient temperature
min/max

5

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values

1SNC160537F0014

RoHS

PC81
8 mm 0.315 in spacing

PC81 lateral jumper bars
Description
Comb-type jumper bar, allows the connection of consecutive blocks or not by one compression clamp
connection.

Ordering details
Description

Color

8 mm 0.315 in spacing

10 poles

Type
Grey

PC81-10

Part Number
1SNA173523R1100

Pkg

Weightqty(1 pce) g

10

5.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Brass/polyamide
V0
I2F3-55 ... +110 °C -67 ... +230 °F-55 ... +110 °C -67 ... +230 °F-5 ... +40 °C-23 ... +104 °F

RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

1SNK161060S0201

All the main technical data provided are "manufacturer" values

Circuit separators
Screw clamp terminal block accessories

CS circuit separators
1SNK160002F0014

Description–– The CS circuit separator avoids the derating of terminal blocks when cut jumper bars JB are used,–– Compatible with feed-through terminal blocks up to 16 mm² 4 AWG,–– Without spacing loss.

Ordering details

CS

Description

0 mm 0 in spacingColor

0 mm 0 in spacing

Mounting instructions

Type

Dark grey

CS

Part Number
1SNK900101R0000

Pkg

Weightqty(1 pce) g

20

0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

5

1SNK160003F0014

CS-R1 circuit separators

CS-R1

Description–– Ease the visual identification of the several circuits within your terminal block assemblies,–– Compatible with feed-through terminal blocks up to 35 mm² 0 AWG,–– Intermediate cover holder for CO protective cover,–– Mounting on DIN3-TH35 rail.

Ordering details

71 2.79"

69 2.72"

61.5 2.42"

Description

Color

3 mm 0.118 in spacing

Dark grey

CS-R1

Part Number

Pkg

Weightqty(1 pce) g

1SNK900103R0000

20

5.20

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications

35 1.38"

3 mm 0.118 in spacing

Type

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Mounting instructions
All the main technical data provided are "manufacturer" values
RoHS

Description
Terminal block markers
Blank card

In polycarbonate
Blank card
Universal wire markers holder 5.2 mm 0.205 in spacing

Color
White

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Technical data valid for copper conductors only.

PAGE 227

1SNK160018S0201

Accessories

1SNK160149F0014

Shield connectors
Screw clamp terminal block accessories

SHBS/SHB

SHBS/SHB shield connectors
Description–– Ensure the continuity of your shield connection,–– Various connection solutions available: RILS cable ties, soldering, quick-connect.

Ordering details
13.67 .54"

Description

128 5.04"
SHB

Compatible with ZS feed-through terminal blocks
Compatible with ZS and ZK double deck terminal blocks

Type
SHBS
SHB

Part Number
1SNK900600R0000
1SNK900602R0000

Pkg

Weightqty(1 pce) g

20
20

3.50
4.90

Main technical data
Material specifications
10.87 .43"

SHBS
94 3.70"

Color

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

SHBS
Rated voltage-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
320 V

UL - CSA

Ex e
125 V

All the main technical data provided are "manufacturer" values
RoHS

Accessories for screw clamp and PI-Spring terminal blocks
Description
Cable ties

Color
For SNK shield connector

Type
RILS

Part Number
1SNK900627R0000

Pkg

Weightqty(1 pce) g

10

0.30

Mounting instructions–– SHBS is directly fixed on the terminal block,–– SHB is fixed on the ES4-D2 end section,–– SHBP is directly fixed on the terminal block,–– Connect the cable shielding on the shielding connector with:–– RILS cable ties,–– quick-connect (the shield connector needs to beprepared),–– soldering iron.

1SNK160079S0201

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPL protecting covers
Screw clamp terminal block accessories

1SNK160096F0014

Description

PL

Mounting instructions–– Prohibit access to the screw clamps,–– Indicate live circuits.

Ordering details
Description

Color

5.2 mm 0.205 in spacing
6 mm 0.236 in spacing
8 mm 0.315 in spacing
10 mm 0.394 in spacing
16 mm 0.630 in spacing

Transparent

Type
PL5
PL6
PL8
PL10
PL16

Main technical data
Material specifications
Ambient temperature
min/max–– The mounting of the PL does not require a screwdriver,–– The dismounting of the PL requires a

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900618R0000
1SNK900619R0000
1SNK900620R0000
1SNK900621R0000
1SNK900622R0000

Pkg

Weightqty(1 pce) g

10
10
10
10
10

1.50
1.80
2.60
3.10
4.60

Mounting instructions
Polycarbonate
V2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

Flat screwdriverØ 4 mmØ 0.157 in

All the main technical data provided are "manufacturer" values
RoHS

screwdriver DIA .4 mm 0.160 in, thescrewdriver must be positionned in the
cover centered hole.

1SNK160021S0201

5

Technical data valid for copper conductors only.

PAGE 229

1SNK160110F0014

Protecting covers
Screw clamp terminal block accessories

CO protecting covers
Description–– Restrict access to your assembly with the protecting cover CO installed with KCO mounting kit (2 end stops,
2 sealing accessories),–– Compatible with SNK feed-through terminal blocks up to 35 mm² 0 AWG.

CO

Ordering details
Description
30.2 1.19"

77 3.03"Color

1 m 39.4 in length

TypeTransparent

COPart Number

Pkg

Weightqty(1 pce) g

1SNK900604R0000

1

300.00Part Number

Pkg

Weightqty(1 pce) g

1
20

47.80
27.00

Main technical data
Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Material specifications
Ambient temperature
min/max

PVC
V0-55 ... +80 °C-55 ... +80 °C-5 ... +40 °C-67 ... +176 °F-67 ... +176 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Protecting cover kits
Label

Mounting kit for cover CO

Dark grey
White

Type
KCO
PAM43020

1SNK900624R0000
1SNA235106R2600

Mounting instructions
Restrict access to the circuit by sealing the cover:–– Drill on the CO center line at 5 mm 0.197 in fromthe extremity with 5 mm 0.197 in diameter drill,–– Pass the sealing collar through the CO and KCO holes.

5

KCO protecting cover kits
1SNK160144F0014

Description
Mount your protecting cover with the KCO versatile mounting kit (2 end stops, 2 sealing accessories):–– Maintain the cover,–– Reliably seal the access to the terminal assembly if needed,–– Use it as well as an end stop.

Ordering details
Description
74.4 2.93"

65.7 2.59"

Mounting kit for cover CO
73.2 2.88"

37.2 1.46"

Color
Dark grey

Type
KCO

Part Number

Pkg

Weightqty(1 pce) g

1SNK900624R0000

1

47.80

Rail

G32, TH 35-7.5,
TH 35-15, TH 15-5.5
Flat screwdriverØ 4 mmØ 0.157 in

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

All the main technical data provided are "manufacturer" values
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPolyamide
V0-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

1SNK160045S0201

KCO

SC-JB88 mm 0.315 in spacing

SC-JB8 short circuit bridges
Description–– Allow safe short-circuiting of current Tranformers circuits,–– Insulated,–– Fully operated by screwdriver,–– Short circuited fixed position secured thanks to AJS9 tightening,–– Adapted hook shape maintains the bridge on the terminal block in the non short-circuited position,–– The orange version can be used as fixed jumpers.

Ordering details
Description

Color

8 mm 0.315 in spacing

2 poles
3 poles
4 poles
3/5 poles
3 poles
4 polesType
Yellow

OrangeSC-JB8-2
SC-JB8-3
SC-JB8-4
SC-JB8-5
SC-JB8-3-OR
SC-JB8-4-OR

Part Number
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNK900655R0000
1SNK900657R0000
1SNK900658R0000

Pkg

Weightqty(1 pce) g

25
25
25
25
25
25

2.00
3.4
4.7
4.7

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

5

1SNK161063S0201

1SNK160221F0014

Short circuit bridges
Screw clamp terminal block accessories

Technical data valid for copper conductors only.

PAGE 231

1SNC160482F0014

Test sockets
Screw clamp terminal block accessories

AJS
4 mm 0.157 in spacing

AJS test sockets
Description–– Insulated test sockets,-- Many colors available for circuit identification,-- Compatible with standard DIA 4 mm 0.157 in test plugs:-- insulated (according to IEC 60101-031) - not insulated (with mobile protection),-- Compatible with ZS10-ST…SNK series terminal blocks, M6/8.ST...SNA series terminal blocks, D6/8.
ST.RS..Solution series terminal blocks

Ordering details
Description

Color

Test sockets DIA 4 mm 0.157 in

Type
Grey
Blue
Yellow
GreenRed
Purple
Brown
White
Black

AJS9-GRAJS9-BLAJS9
AJS9-GN
AJS9-RDAJS9-PR
AJS9-BR
AJS9-WH
AJS9-BK

Main technical data
Material specifications
Ambient temperature
min/max

1SNA206682R0300
1SNA206683R0400
1SNA179726R0200
1SNA206681R0200
1SNA206720R1400
1SNA206772R0000
1SNA206782R0000
1SNA206765R0000
1SNA206680R1500

Pkg

Weightqty(1 pce) g

25
25
25
25
25
25
25
25
25

3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60

Mounting instructions
Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.5 Nm ± 0.1
4.42 lb.in ± 0.88

All the main technical data provided are "manufacturer" values
RoHS

1SNK161064S0201

5

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS1SNK160301V0014

End sections
Pluggable terminal block accessories

EDK2.5-22

EDK2.5-22 end sections
Description–– Compatible with ZDK2.5-22 and ZDK4-22 pluggable terminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g

2.2 mm 0.087 in spacing

Dark grey

EDK2.5-22

1SNK805910R0000

20

3.08

1SNK164030V0014

EDK2.5-21 end sections
Description–– Compatible with ZDK2.5-11, ZDK2.5-11-BL and ZDK2.5-11-PE pluggable terminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g

1.5 mm 0.059 in spacing

Dark grey

EDK2.5-21

1SNK805914R0000

20

1.90

EDK2.5-21

EDK2.5-11 end sections
1SNK164029V0014

Description–– Compatible with ZD2.5-11 pluggable terminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g

1.5 mm 0.059 in spacing

Dark grey

EDK2.5-11

1SNK805915R0000

20

1.49

5

EDK2.5-11

EDK2.5-D end sections
1SNK164031V0014

Description–– Compatible with ZDK2.5-D2, ZDK2.5-D2-BL, ZDK2.5-D1, ZDK2.5-D1-PE and ZDK2.5-D2-PE pluggableterminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g2 mm 0.079 in spacing

Dark grey

EDK2.5-D

1SNK805913R0000

20

3.88

EDK2.5-D

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °C-67 ... +230 °C+23 ... +104 °C
1SNK164033S0201

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 233

End sections
Pluggable terminal block accessories

1SNK164028V0014

ED2.5-22 end sections
Description–– Compatible with ZD2.5-22 and ZD2.5-22-PE pluggable terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

ED2.5-22

Dark grey

TypePart Number

ED2.5-22

1SNK805917R0000

TypePart Number

Pkg

Weightqty(1 pce) g

20

3.64

1SNK160302V0014

EDS4-22 end sections

EDS4-22

Description–– Compatible with ZDS4-22 pluggable terminal block.

Ordering details
Description

Color

0.8 mm 0.031 in spacing

Dark grey

EDS4-22

1SNK805911R0000

Pkg

Weightqty(1 pce) g

20

1.85

5

Main technical data

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS-67 ... +230 °C-67 ... +230 °C+23 ... +104 °C
1SNK164034S0201

Material specifications

Coding pegs - Locking devices
Pluggable terminal block accessories

COP coding pegs
1SNK160298V0014

Description–– The coding pegs prevent plugs to be inserted into the wrong circuit.

Ordering details
Description

Color

Type

Dark grey

COP-ZDPart Number
1SNK900636R0000

Pkg

Weightqty(1 pce) g

10

3.57

Main technical data

COP

Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions

5

VR locking devices
1SNK160315V0014

Description–– Automatic locking providing excellent plug withstand in case of accidental pulling,–– Lock safely one or two CDK or CDS plugs on ZDK and ZDS pluggable terminal blocks,–– Install one VR... up to 8 poles plugs assembly and two VR... up to 15 poles assembly.

Ordering details
Description

Color

VR

9.4 mm 0.370 in spacing

9.4 mm 0.370 in spacing

Main technical data
Material specifications

Ambient temperature
min/max

Type
Black

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

VR-ZD

Part Number
1SNK900637R0000

Pkg

Weightqty(1 pce) g50

6.5

Polyacetal
HB-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values.
RoHS

1SNK164009S0201

Mounting instructions

Technical data valid for copper conductors only.

PAGE 235

Summary_6

6

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSSNK series, marking solutions

Selection guide				238-239

MG3 thermal transfer printer		

240-241

AMS 600 and AMS 250 plotter		

242-243

Terminal block markers
5.2 mm 0.205 in spacing
MC512, MG-CPM-13

Blank card in polycarbonate		Blank card in polyamide		
MC512PA						
Pre-printed marker card for horizontal terminal block assembly

244
245
246-247

				Pre-printed marker card for vertical terminal block assembly 248-249
6 mm 0.236 in spacing
MC612, MG-CPM-13 		

Blank card in polycarbonate		

250

MC612PA		
Blank card in polyamide		

251

			
Pre-printed marker card for horizontal terminal block assembly 252-253
				Pre-printed marker card for vertical terminal block assembly

254

8 mm 0.315 in spacing
Blank card		
MC812, MC812PA		
MC812PA		Pre-printed marker card for horizontal terminal block assembly

256257-258

				Pre-printed marker card for vertical terminal block assembly 259-260
Markers
UMH			

Universal wire markers holder		MG2-TDMO		

Clip-on blank wire marker		

261
261

MG-TAR, MG-TAA		Markers for components		

262

MG-TAPW		

Markers for components		

263

MCLH

Label		

264

Marking systems
6

Consumable		265HTP500		
Thermal transfer printer		

266

Plotter		

267-268

Summary_6

MG3		
AMS 			

PAGE 237

Marking systems
Selection guide

For versatile applications

Marking systems

MG3

Technology

Thermal transfer

Printing mode

ManualPrinting speed

MediumPrinting quality

300 x 600 dpi

1 ribbon or ink cartridge printing capacity~ 160 000, MG-CPM (5 x 10 mm markers)

Printing color available (monochrome)

Black / Red / Blue / Green / White

Terminal block markers material

Polycarbonate

Terminal block markers

6

SNK series terminal blocks blank markers polyamide–

SNK series terminal blocks blank markers polycarbonate

MG-CPM

SNK series terminal blocks blank markers PVC

MG-CPMF

End stop markers

2 marker types

Other terminal blocks manufacturers blank markers

15 manufacturers

Wires and cables markers

4 marker types

Components and equipment markers

9 marker types

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSFor basic marking applications

AMS 600 - AMS 250
PlotterManualLow
300 x 300 dpi~ 230 000 markers (with 3 characters per markers)
Black
Polyamide

MC…PA
–
–
6

4 marker types
5 manufacturers
1 marker type

1SNC160226S0201

9 marker types

PAGE 239

MG3 thermal transfer printerThe versatile, compact androbust marking system
MARKINGenius® MG3 is a high resolution printer based onthermal transfer technology for producing high quality identification and labelling for terminal blocks, cables and all equipment mounted in electrical panels.
Compact, ergonomic, clean and quiet, MARKINGenius® MG3
may be conveniently located in an office or workshop or easilytransported in the field.
Thermal transfer technology uses heat to transfer charactersor symbols onto a plastic marker through an ink ribbon.
Besides the excellent printing quality, there is no drying time
and the markers are instantly usable.
With the MG3 thermal transfer printer, forget about drying
times and clogged print head problems.

Combined simplicity, performanceand make savings
Facilitate your printing process
Compact design (382 x 230 x 230 mm) facilitates
use in workshops or in the field.
Easy to install and use: comprehensive quickstart kit. Intuitive software with easy data importand entry.
Versatile: many different media available: plastic
markers, stickers, labels etc.
Save time and consumables
Gain time with a short printing process:12 seconds cycle. Carriage loading and unloading
operation is fast and simple.
Economic: up to 300 000 markers with one ribbon.
Partially printed marker card may be reused to
avoid wastage.
No drying time: printed markers are immediately
ready to use.
Experience quality
High Quality printing: 300 x 600 dpi for image orgraphic printing.
Robust: all moving parts are in metal.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSHigh quality printing

Short printing cycle of 12 seconds

Economic: up to 300 000 markers
with one ribbon

Many media types available forprinting

1SNC160211S0201

6

MG3 thermal transfer printerComponents of the kit

The MG3 printer is delivered with a comprehensive set ofaccessories for getting started quickly
Kit (Part number: 1SNB419001R0000) including:–– 1 Thermal transfer printer–– 1 Software CD–– 1 Power supply cable–– 1 USB cable–– 1 Installation, operating, maintenanceand user documentation–– 1 Protective cover–– 1 Ribbon take up spool–– 1 MG2-QTB support plate for terminal block markers(MG-CPM-01, 02, 03, 04, 07)–– 1 MG2-PWC support plate for wire and cable markers(MG-TPM)–– 1 MG2-PLT support plate for wire and cable markers(MG-TPMF) and various labels and signs–– 1 MG2-ETB Support plate for SNK series terminal block
markers (MG-CPM-13)–– 1 MG2-ETR Black printing ribbon.

6– – Optimised printing of media for cables, terminal blocks,
control gear, connectors, push buttons, components,
panels and self-adhesive labels– – Specially developed proprietary Genius font and also
Windows fonts– – Designs customised media– – Vector, drawing and clip art printing– – Free upgrades for each new release– – Microsoft® Windows® XP, Windows Vista®,
Windows 2000 SP4 ®, Windows 7®.

1SNC160211S0201

Genius Pro software
The Genius Pro software application benefits from long experience in the field and requires the operator to have only basic
skills in order to use it. It is application-oriented and provides
fast and easy data entry including a dynamic full-size media
preview giving an accurate representation of the current job.
Features / characteristics:–– More than ten types of counter such as *.txt, *.cad, *.dbf,*.xls can be imported–– AutoCAD, Elcad, Spac and Excel import–– MATRIX, ACS and Simplo conversion

PAGE 241AMS 600 and AMS 250 plotter
The universal standard for printing jobs

AMS 600
Universal printing plotter
Compatible with all original manufacturer terminal block markers (polyamide), it can also print other identification supports
such as: wire and cable markers, push buttons, panels…
This plotter offers a large working area, hosting up to 4 different support plates for one plot job.
Error detection mode
The A3 panel automatically recognises the support plate andavoids the need to select marking elements, it also warns theuser when the support is wrongly installed.
Dry out protection system
Pens are prevented from drying out thanks to AMS 600 integrated pen station.

AMS 2506

1SNC160215S0201

Compact
This A4 plotter is smaller than AMS 600 and is more suited toa cluttered environment.

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSAutomatic installation
The installation program starts automatically. The computer
just needs to be rebooted after it has finished and printing canstart.

Microsoft, Windows, Excel are trademarks of Microsoft Corporation.

What you see is what you get !

User friendly
Microsoft® Windows® software

Time saving: data import function
from CAD, TXT and Excel® files

6

1SNC160215S0201

New special ink disposable plotter pens ED-R–– Disposable pens ED-R almost never clog, they are ideal foruse in particularly dry environments.
–– These pens are filled with the permanent ink ED, most suitable for marking various plastic surfaces.
–– The ED ink should only be used on plastic material. Do notclean or touch with aggressive fluids.
–– For applications outside of the control panel the ink P 2.0
is more suitable and durable.

PAGE 243

Terminal block markers
Blank card in polycarbonate - 5.2 mm 0.205 in spacing

MC512 terminal block markers
Description
MC512–– MC512 marker card in polycarbonate for high marking quality, durability and speed when marked with the
HTP500 printer,–– Excellent marking durability in the most severe environments,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in).

Main technical data

HTP500-V2

Material

Flammability

Maximum printed digits

Polycarbonate

V0

Horizontal

Number of markers
per card
45

Color

3

Vertical8

Dimensionsmm
4.8 x 12inches
0.189 x 0.472

Ordering details
Description
Blank card

TypePart Number

MC512
MC512-YLWhite
Yellow

Pkg

1SNK140000R0000
1SNK140004R0000

Weightcard(1 pce) g

22
22

9.00
9.00

MG-CPM-13 terminal block markers
Description–– MG-CPM-13 41790 and 41740 markers are used for marking 5.2 mm 0.205 in spacing SNK terminal blocks,–– Provide an elevate mechanical robustness, high dimensional stability and are halogen free,–– Single application on terminal block,–– 35 cards per packing

Main technical data
MG-CPM-13

Material

Flammability

Maximum printed digits

Polycarbonate

V2

Horizontal

Number of markers
per card
56

Color

3

Vertical8

Dimensionsmm
4.8 x 12inches0.196 x 0.472

Ordering details

6

Description
Blank card

TypePart Number

Pkg

Weight

0.232
0.232

marker (1 pce) g

White
Yellow

MG-CPM 13 41790
MG-CPM 13 41740

1SNB041790R0512
1SNB041740R0512

1960
1960

Type

Part Number

Pkg

Marking systems
Description
MG3 KIT

Thermal transfer printerWeightqty(1 pce) g

12600.00

MG3 KIT

1SNB419001R0000

1

Type

Part Number

Pkg

Marking systems accessories
Description

MG2-ETB 991016 1SNB991016R0000(1 pce) g

1100.00

1SNK160003S0201 - Rev. A

Support plate for MG-CPM-13

Weightqty

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSTerminal block markers
Blank card in polyamide - 5.2 mm 0.205 in spacing

MC512PA terminal block markers
Description
MC512PA–– MC512PA marker card in polyamide to be marked on AMS 600 marking table for medium scale volumes
and standard industrial applications,–– Terminal blocks are directly independent after strip mounting,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in).

Main technical data
Material

Flammability

Maximum printed digits

Polyamide

V2

Horizontal

Number of markers
per card
100

Color

3

Vertical8

Dimensionsmm
4.8 x 12inches
0.189 x 0.472

Ordering details
Description
Blank card

White

Part Number

Pkg

Weightcard(1 pce) g

10.00

MC512PA1SNK149999R0000

20

Type

Part Number

Pkg

Marking systems
Description
AMS plotter

Weightqty(1 pce) g

12600.00

AMS 600 KIT

1SNA360000R2400

1

Type

Part Number

Pkg

Marking systems accessories
Description
Marking support plate for MC PA marker cards(3 MC PA marker cards per plate)

SPRC 30-3

1SNA360039R1700

Weightqty(1 pce) g

1300.00

6

1SNK160076S0201

AMS 600

Type

PAGE 245

MC512PA terminal block markers
Pre-printed marker card for horizontal terminal block assembly
Description
Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols.

Main technical data
MC512PAMaterial

Flammability

Polyamide

V2

Dimensionsmm
4.8 x 12inches
0.189 x 0.472

Ordering details
Color

Type

Part NumberPkg

0->9 (x10)
1->10 (x10)
11->20 (x10)
21->30 (x10)
31->40 (x10)
41->50 (x10)
51->60 (x10)
61->70 (x10)
71->80 (x10)
81->90 (x10)
91->100 (x10)
101->110 (x10)
111->120 (x10)
121->130 (x10)
131->140 (x10)
141->150 (x10)
151->160 (x10)161->170 (x10)
171->180 (x10)
181->190 (x10)
191->200 (x10)

Number ofmarkers per card
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK140091R0000
1SNK140011R0000
1SNK140021R0000
1SNK140031R0000
1SNK140041R0000
1SNK140051R0000
1SNK140061R0000
1SNK140071R0000
1SNK140081R0000
1SNK140083R0000
1SNK140101R0000
1SNK140111R0000
1SNK140121R0000
1SNK140131R0000
1SNK140141R0000
1SNK140151R0000
1SNK140161R0000
1SNK140171R0000
1SNK140181R0000
1SNK140191R0000
1SNK140201R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

Weight
g
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900

100
100
100
100
100
100
100
100
100

White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK145011R0000
1SNK145021R0000
1SNK145031R0000
1SNK145041R0000
1SNK145051R0000
1SNK145061R0000
1SNK145071R0000
1SNK145081R0000
1SNK145091R0000

1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK146011R0000
1SNK146021R0000
1SNK146031R0000
1SNK146041R0000
1SNK146051R0000
1SNK146061R0000
1SNK146071R0000
1SNK146081R0000
1SNK146091R0000
1SNK146101R0000
1SNK146111R0000
1SNK146121R0000
1SNK146131R0000
1SNK146141R0000
1SNK146151R0000
1SNK146161R0000
1SNK146171R0000
1SNK146181R0000
1SNK146191R0000
1SNK146201R0000
1SNK146211R0000
1SNK146221R0000
1SNK146231R0000
1SNK146241R0000
1SNK146251R0000

5.2 mm 0.205 in spacing

6

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

White

card

(1 pce)

1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
Continue on next page →1SNK160004S0201 - Rev. A

Description

MC512PA terminal block markers
Pre-printed marker card for horizontal terminal block assembly
Ordering details

MC512PA

5.2 mm 0.205 in spacing

Number ofmarkers per card

← Continuation of previous page
Z (x100)100
0 (x100)100
1 (x100)100
2 (x100)100
3 (x100)100
4 (x100)100
5 (x100)100
6 (x100)100
7 (x100)100
8 (x100)100
9 (x100)
100

Color

Type

Part Number

Pkg

White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK146261R0000
1SNK147001R0000
1SNK147011R0000
1SNK147021R0000
1SNK147031R0000
1SNK147041R0000
1SNK147051R0000
1SNK147061R0000
1SNK147071R0000
1SNK147081R0000
1SNK147091R0000

1
1
1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PA1SNK148001R0000
1SNK148011R0000
1SNK148021R0000
1SNK148031R0000
1SNK148041R0000

1
1
1
1
1

10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK148051R0000
1SNK148061R0000
1SNK148071R0000
1SNK148091R0000
1SNK148101R0000
1SNK148111R0000
1SNK148121R0000
1SNK148131R0000
1SNK148141R0000
1SNK148151R0000
1SNK148161R0000
1SNK148171R0000
1SNK148181R0000
1SNK149001R0000
1SNK149011R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

White
White
White
White
White
White
White
White
White
White

+ (x100)- (x100)~ (x100)= (x100)(x100)

100
100
100
100
100

White

L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)
L1-L2-L3-N-PE (x20)
U1-U2-U3-V1-V2-V3-W1W2-W3 (x10) + U1 (x10)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White

card

Weightg(1 pce)6

1SNK160004S0201 - Rev. A

Description

PAGE 247

MC512PA terminal block markers
Pre-printed marker card for vertical terminal block assembly
Description
Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols.

Main technical data
MC512PAMaterial

Flammability

Polyamide

V2

Dimensionsmm
4.8 x 12inches
0.189 x 0.472

Description

5.2 mm 0.205 in spacing6

0->9 (x10)
1->10 (x10)
11->20 (x10)
21->30 (x10)
31->40 (x10)
41->50 (x10)
51->60 (x10)
61->70 (x10)
71->80 (x10)
81->90 (x10)
91->100 (x10)
101->110 (x10)
111->120 (x10)
121->130 (x10)
131->140 (x10)
141->150 (x10)
151->160 (x10)161->170 (x10)
171->180 (x10)
181->190 (x10)
191->200 (x10)

Number ofmarkers per card
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900
901->1000
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color

Type

Part Number

Pkg

Weightcard(1 pce) g

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK140092R0000
1SNK140012R0000
1SNK140022R0000
1SNK140032R0000
1SNK140042R0000
1SNK140052R0000
1SNK140062R0000
1SNK140072R0000
1SNK140082R0000
1SNK140084R0000
1SNK140102R0000
1SNK140112R0000
1SNK140122R0000
1SNK140132R0000
1SNK140142R0000
1SNK140152R0000
1SNK140162R0000
1SNK140172R0000
1SNK140182R0000
1SNK140192R0000
1SNK140202R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

100
100
100
100
100
100
100
100
100
100

White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK145012R0000
1SNK145022R0000
1SNK145032R0000
1SNK145042R0000
1SNK145052R0000
1SNK145062R0000
1SNK145072R0000
1SNK145082R0000
1SNK145092R0000
1SNK145102R0000

1
1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK146012R0000
1SNK146022R0000
1SNK146032R0000
1SNK146042R0000
1SNK146052R0000
1SNK146062R0000
1SNK146072R0000
1SNK146082R0000
1SNK146092R0000
1SNK146102R0000
1SNK146112R0000
1SNK146122R0000
1SNK146132R0000
1SNK146142R0000
1SNK146152R0000
1SNK146162R0000
1SNK146172R0000
1SNK146182R0000
1SNK146192R0000
1SNK146202R0000
1SNK146212R0000
1SNK146222R0000

White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
1
10.00
Continue on next page →1SNK160005S0201 - Rev. A

Ordering details

MC512PA terminal block markers
Pre-printed marker card for vertical terminal block assembly
Ordering details

MC512PA

5.2 mm 0.205 in spacing

Number ofmarkers per card

← Continuation of previous pageW (x100)
100
X (x100)
100
Y (x100)
100
Z (x100)
100

Color

White
White
White
White

0 (x100)
1 (x100)
2 (x100)
3 (x100)
4 (x100)
5 (x100)
6 (x100)
7 (x100)
8 (x100)
9 (x100)

100
100
100
100
100
100
100
100
100
100

White

+ (x100)- (x100)~ (x100)= (x100)(x100)

100
100
100
100
100

White

L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)+24V (x100)+48V (x100)-24V (x100)-48V (x100)
L1-L2-L3-N-PE (x20)
U1-U2-U3-V1-V2-V3-W1W2-W3 (x10) + U1 (x10)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White
White
White
White
White
White

White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

Type

Part Number

Pkg

Weightcard(1 pce) g

MC512PAMC512PAMC512PAMC512PA1SNK146232R0000
1SNK146242R0000
1SNK146252R0000
1SNK146262R0000

1
1
1
1

10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK147002R0000
1SNK147012R0000
1SNK147022R0000
1SNK147032R0000
1SNK147042R0000
1SNK147052R0000
1SNK147062R0000
1SNK147072R0000
1SNK147082R0000
1SNK147092R0000

1
1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PA1SNK148002R0000
1SNK148012R0000
1SNK148022R0000
1SNK148032R0000
1SNK148042R0000

1
1
1
1
1

10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK148052R0000
1SNK148062R0000
1SNK148072R0000
1SNK148092R0000
1SNK148102R0000
1SNK148112R0000
1SNK148122R0000
1SNK148132R0000
1SNK148142R0000
1SNK148152R0000
1SNK148162R0000
1SNK148172R0000
1SNK148182R0000
1SNK148192R0000
1SNK148202R0000
1SNK148212R0000
1SNK148222R0000
1SNK149002R0000
1SNK149012R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

6

1SNK160005S0201 - Rev. A

Description

PAGE 249

Terminal block markers
Blank card in polycarbonate - 6 mm 0.236 in spacing

MC612 terminal block markers
Description
MC612–– MC612 marker card in polycarbonate for high marking quality, durability and speed when marked with the
HTP500 printer,–– Excellent marking durability in the most severe environments,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in).

Main technical data
Material

Flammability

Maximum printed digits

Polycarbonate

V0

Horizontal

Number of markers
per card
39

Color

3

Vertical8

Dimensionsmm
5.6 x 12inches0.220 x 0.472

Ordering details
HTP500-V2

Description
Blank card

TypePart number

MC612
MC612-YLWhite
Yellow

1SNK150000R0000
1SNK150004R0000

Pkg

Weightcard(1 pce) g

22
22

10.00
10.00

MG-CPM-13 terminal block markers
Description–– MG-CPM-13 41791 and 41741 markers are used for marking 6 mm 0.236 in spacing SNK terminal blocks,–– Provide an elevate mechanical robustness, high dimensional stability and are halogen free,–– Single application on terminal block,–– 35 cards per packing.

Main technical data
MG-CPM-13

Material

Flammability

Maximum printed digits

Polycarbonate

V0

Horizontal

Number of markers
per card
48

Color

3

Vertical8

Dimensionsmm
5.6 x 12inches
0.236 x 0.472

Ordering details

6

Description
Blank card

TypePart number

Pkg

Weightmarker (1 pce) g

White
Yellow

MG-CPM 13 41791
MG-CPM 13 41741

1SNB041791R0612
1SNB041741R0612

1680
1680

Type

Part number

Pkg

0.273
0.273

Marking systems
Description
MG3 KIT

Thermal transfer printerWeightqty(1 pce) g

12600.00

MG3 KIT

1SNB419001R0000

1

Type

Part number

Pkg

Weightqty(1 pce) g

1100.00Marking systems accessories
Description

MG2-ETB 991016 1SNB991016R0000

1SNK160006S0201 - Rev. A

Support plate for MG-CPM-13

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSTerminal block markers
Blank card in polyamide - 6 mm 0.236 in spacing

MC612PA terminal block markers
Description
MC612–– MC612PA marker card in polyamide to be marked on AMS 600 marking table for medium scale volumes
and standard industrial applications,–– Terminal blocks are directly independent after strip mounting,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in).

Main technical data
Material

Flammability

Maximum printed digits

Polyamide

V2

Horizontal

Number of markers
per card
100

Color

3

Vertical8

Dimensionsmm
5.6 x 12inches0.220 x 0.472

Ordering details
Description
Blank card

White

Part Number

Pkg

Weightcard(1 pce) g

11.00

MC612PA1SNK159999R0000

20

Type

Part Number

Pkg

Marking systems
Description
AMS plotter

Weightqty(1 pce) g

12600.00

AMS 600 KIT

1SNA360000R2400

1

Type

Part Number

Pkg

Weightqty(1 pce) g

1300.00Marking systems accessories
Description
Marking support plate for MC PA marker cards(3 MC PA marker cards per plate)

SPRC 30-3

1SNA360039R1700

6

1SNK160077S0201

AMS 600

Type

PAGE 251

MC612PA terminal block markers
Pre-printed marker card for horizontal terminal block assembly
Description
Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols.

Main technical data
MC612PAMaterial

Flammability

Polyamide

V2

Dimensionsmm
5.6 x 12inches0.220 x 0.472

Ordering details

6 mm 0.236 in spacing6

0->9 (x10)
1->10 (x10)
11->20 (x10)
21->30 (x10)
31->40 (x10)
41->50 (x10)
51->60 (x10)
61->70 (x10)
71->80 (x10)
81->90 (x10)
91->100 (x10)
101->110 (x10)
111->120 (x10)
121->130 (x10)
131->140 (x10)
141->150 (x10)
151->160 (x10)161->170 (x10)
171->180 (x10)
181->190 (x10)
191->200 (x10)

Number ofmarkers per card
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900

100
100
100
100
100
100
100
100
100

White

A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color

Type

Part Number

Pkg

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK150091R0000
1SNK150011R0000
1SNK150021R0000
1SNK150031R0000
1SNK150041R0000
1SNK150051R0000
1SNK150061R0000
1SNK150071R0000
1SNK150081R0000
1SNK150083R0000
1SNK150101R0000
1SNK150111R0000
1SNK150121R0000
1SNK150131R0000
1SNK150141R0000
1SNK150151R0000
1SNK150161R0000
1SNK150171R0000
1SNK150181R0000
1SNK150191R0000
1SNK150201R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

Weight
g
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK155011R0000
1SNK155021R0000
1SNK155031R0000
1SNK155041R0000
1SNK155051R0000
1SNK155061R0000
1SNK155071R0000
1SNK155081R0000
1SNK155091R0000

1
1
1
1
1
1
1
1
1

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK156011R0000
1SNK156021R0000
1SNK156031R0000
1SNK156041R0000
1SNK156051R0000
1SNK156061R0000
1SNK156071R0000
1SNK156081R0000
1SNK156091R0000
1SNK156101R0000
1SNK156111R0000
1SNK156121R0000
1SNK156131R0000
1SNK156141R0000
1SNK156151R0000
1SNK156161R0000
1SNK156171R0000
1SNK156181R0000
1SNK156191R0000
1SNK156201R0000
1SNK156211R0000
1SNK156221R0000
1SNK156231R0000

card

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

(1 pce)

1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
Continue on next page →1SNK160007S0201 - Rev. A

Description

MC612PA terminal block markers
Pre-printed marker card for horizontal terminal block assembly
Ordering details

MC612PA

6 mm 0.236 in spacing

Number ofmarkers per card

← Continuation of previous page
X (x100)
100
Y (x100)
100
Z (x100)
100

Color

White
White
White

0 (x100)
1 (x100)
2 (x100)
3 (x100)
4 (x100)
5 (x100)
6 (x100)
7 (x100)
8 (x100)
9 (x100)

100
100
100
100
100
100
100
100
100
100

White

+ (x100)- (x100)~ (x100)= (x100)
Ground (x100)

100
100
100
100
100

White

L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)
L1-L2-L3-N-PE (x20)
U1-U2-U3-V1-V2-V3-W1W2-W3 (x10) + U1 (x10)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White
White
White
White
White
White

White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White

Type

Part Number

Pkg

Weightcard(1 pce) g

MC612PAMC612PAMC612PA1SNK156241R0000
1SNK156251R0000
1SNK156261R0000

1
1
1

11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK157001R0000
1SNK157011R0000
1SNK157021R0000
1SNK157031R0000
1SNK157041R0000
1SNK157051R0000
1SNK157061R0000
1SNK157071R0000
1SNK157081R0000
1SNK157091R0000

1
1
1
1
1
1
1
1
1
1

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PA1SNK158001R0000
1SNK158011R0000
1SNK158021R0000
1SNK158031R0000
1SNK158041R0000

1
1
1
1
1

11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK158051R0000
1SNK158061R0000
1SNK158071R0000
1SNK158091R0000
1SNK158101R0000
1SNK158111R0000
1SNK158121R0000
1SNK158131R0000
1SNK158141R0000
1SNK158151R0000
1SNK158161R0000
1SNK158171R0000
1SNK158181R0000
1SNK159001R0000
1SNK159011R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

6

1SNK160007S0201 - Rev. A

Description

PAGE 253

MC612PA terminal block markers
Pre-printed marker card for vertical terminal block assembly
Description
Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols.

Main technical data
MC612PAMaterial

Flammability

Polyamide

V2

Dimensionsmm
5.6 x 12inches0.220 x 0.472

Ordering details

6 mm 0.236 in spacing6

0->9 (x10)
1->10 (x10)
11->20 (x10)
21->30 (x10)
31->40 (x10)
41->50 (x10)
51->60 (x10)
61->70 (x10)
71->80 (x10)
81->90 (x10)
91->100 (x10)
101->110 (x10)
111->120 (x10)
121->130 (x10)
131->140 (x10)
141->150 (x10)
151->160 (x10)161->170 (x10)
171->180 (x10)
181->190 (x10)
191->200 (x10)

Number ofmarkers per card
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900
901->1000

100
100
100
100
100
100
100
100
100
100

White

A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Color

Type

Part Number

Pkg

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK150092R0000
1SNK150012R0000
1SNK150022R0000
1SNK150032R0000
1SNK150042R0000
1SNK150052R0000
1SNK150062R0000
1SNK150072R0000
1SNK150082R0000
1SNK150084R0000
1SNK150102R0000
1SNK150112R0000
1SNK150122R0000
1SNK150132R0000
1SNK150142R0000
1SNK150152R0000
1SNK150162R0000
1SNK150172R0000
1SNK150182R0000
1SNK150192R0000
1SNK150202R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

Weight
g
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK155012R0000
1SNK155022R0000
1SNK155032R0000
1SNK155042R0000
1SNK155052R0000
1SNK155062R0000
1SNK155072R0000
1SNK155082R0000
1SNK155092R0000
1SNK155102R0000

1
1
1
1
1
1
1
1
1
1

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK156012R0000
1SNK156022R0000
1SNK156032R0000
1SNK156042R0000
1SNK156052R0000
1SNK156062R0000
1SNK156072R0000
1SNK156082R0000
1SNK156092R0000
1SNK156102R0000
1SNK156112R0000
1SNK156122R0000
1SNK156132R0000
1SNK156142R0000
1SNK156152R0000
1SNK156162R0000
1SNK156172R0000
1SNK156182R0000
1SNK156192R0000
1SNK156202R0000
1SNK156212R0000
1SNK156222R0000
1SNK156232R0000
1SNK156242R0000

card
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

(1 pce)

1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
1
11.00
Continue on next page →1SNK160008S0201 - Rev. A

Description

MC612PA terminal block markers
Pre-printed marker card for vertical terminal block assembly
Ordering details

MC612PA

6 mm 0.236 in spacing

Number of markers
per card← Continuation of previous pageY (x100)
100
Z (x100)
100

Color

Type

Part Number

Pkg
card

White
White

0 (x100)
1 (x100)
2 (x100)
3 (x100)
4 (x100)
5 (x100)
6 (x100)
7 (x100)
8 (x100)
9 (x100)

100
100
100
100
100
100
100
100
100
100

White

+ (x100)- (x100)~ (x100)= (x100)(x100)

100
100
100
100
100

White

L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)+24V (x100)+48V (x100)- 24V (x100)-48V (x100)
L1-L2-L3-N-PE (x20)
U1-U2-U3-V1-V2-V3-W1W2-W3 (x10) + U1 (x10)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White
White
White
White
White
White

White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

Weightg(1 pce)MC612PAMC612PA1SNK156252R0000
1SNK156262R0000

1
1

11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK157002R0000
1SNK157012R0000
1SNK157022R0000
1SNK157032R0000
1SNK157042R0000
1SNK157052R0000
1SNK157062R0000
1SNK157072R0000
1SNK157082R0000
1SNK157092R0000

1
1
1
1
1
1
1
1
1
1

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PA1SNK158002R0000
1SNK158012R0000
1SNK158022R0000
1SNK158032R0000
1SNK158042R0000

1
1
1
1
1

11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK158052R0000
1SNK158062R0000
1SNK158072R0000
1SNK158092R0000
1SNK158102R0000
1SNK158112R0000
1SNK158122R0000
1SNK158132R0000
1SNK158142R0000
1SNK158152R0000
1SNK158162R0000
1SNK158172R0000
1SNK158182R0000
1SNK158192R0000
1SNK158202R0000
1SNK158212R0000
1SNK158222R0000
1SNK159002R0000
1SNK159012R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

6

1SNK160008S0201 - Rev. A

Description

PAGE 255

MC812 terminal block markers
Blank card in polycarbonate or polyamide - 8 mm 0.315 in spacing

MC812 terminal block markers
Description
MC812–– MC812 marker card in polycarbonate for high marking quality, durability and speed when marked with the
HTP500 printer,–– Excellent marking durability in the most severe environments,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in)Main technical data
Material

Flammability

Maximum printed digits

Polycarbonate

V0

Horizontal

Number of markers
per card
30

Color

4

Vertical8

Dimensionsmm
7.6 x 12inches
0.299 x 0.472

Ordering details
HTP500-V2

Description
Blank card

TypePart number

MC812
MC812-YLWhite
Yellow

1SNK160000R0000
1SNK160004R0000

Pkg

Weightcard(1 pce) g

22
22

10.00
10.00

MC812PA terminal block markers
Description

MC812PA–– MC812PA marker card in polyamide to be marked on AMS 600 marking table for medium scale volumes
and standard industrial applications,–– Terminal blocks are directly independent after strip mounting,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in)Main technical data
Material

Flammability

Maximum printed digits

Polyamide

V2

Horizontal

Number of markers
per card
100

Color

3

Vertical8

Dimensionsmm
7.6 x 12inches
0.299 x 0.472

Ordering details

6

Description
Blank card
AMS 600

TypePart number

Pkg
card

White

Weightg
14.00(1 pce)MC812PA1SNK169999R0000

20

Type

Part number

Pkg

Weightqty(1 pce) g

12600.00

Marking systems
Description
AMS plotter

AMS 600 KIT

1SNA360000R2400

1

Type

Part number

Pkg

Weightqty(1 pce) g

1300.00Marking systems accessories
Description

SPRC 30-3

1SNA360039R1700

1SNK160009S0201 - Rev. A

Marking support plate for MC PA marker cards(3 MC PA marker cards per plate)

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSMC812PA terminal block markers
Pre-printed marker card for horizontal terminal block assembly
Description
Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols.

Main technical data
MC812PAMaterial

Flammability

Polyamide

V2

Dimensionsmm
7.6 x 12inches
0.299 x 0.472

Part Number

Pkg

Weightcard(1 pce) g

Ordering details

8 mm 0.315 in spacing

0->9 (x10)
1->10 (x10)
11->20 (x10)
21->30 (x10)
31->40 (x10)
41->50 (x10)
51->60 (x10)
61->70 (x10)
71->80 (x10)
81->90 (x10)
91->100 (x10)
101->110 (x10)
111->120 (x10)
121->130 (x10)
131->140 (x10)
141->150 (x10)
151->160 (x10)161->170 (x10)
171->180 (x10)
181->190 (x10)
191->200 (x10)

Number ofmarkers per card
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

Color

1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900

100
100
100
100
100
100
100
100
100

White

A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

Type
MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK160091R0000
1SNK160011R0000
1SNK160021R0000
1SNK160031R0000
1SNK160041R0000
1SNK160051R0000
1SNK160061R0000
1SNK160071R0000
1SNK160081R0000
1SNK160083R0000
1SNK160101R0000
1SNK160111R0000
1SNK160121R0000
1SNK160131R0000
1SNK160141R0000
1SNK160151R0000
1SNK160161R0000
1SNK160171R0000
1SNK160181R0000
1SNK160191R0000
1SNK160201R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK165011R0000
1SNK165021R0000
1SNK165031R0000
1SNK165041R0000
1SNK165051R0000
1SNK165061R0000
1SNK165071R0000
1SNK165081R0000
1SNK165091R0000

1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166011R0000
1SNK166021R0000
1SNK166031R0000
1SNK166041R0000
1SNK166051R0000
1SNK166061R0000
1SNK166071R0000
1SNK166081R0000
1SNK166091R0000
1SNK166101R0000
1SNK166111R0000
1SNK166121R0000
1SNK166131R0000
1SNK166141R0000
1SNK166151R0000
1SNK166161R0000
1SNK166171R0000
1SNK166181R0000
1SNK166191R0000
1SNK166201R0000
1SNK166211R0000
1SNK166221R0000

1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
Continue on next page →PAGE 257

6

1SNK160010S0201 - Rev. A

Description

MC812PA terminal block markers
Pre-printed marker card for horizontal terminal block assembly
Ordering details
Description

MC812PA

6← Continuation of previous pageW (x100)
100
X (x100)
100
Y (x100)
100
Z (x100)
100

Color

White
White
White
White

0 (x100)
1 (x100)
2 (x100)
3 (x100)
4 (x100)
5 (x100)
6 (x100)
7 (x100)
8 (x100)
9 (x100)

100
100
100
100
100
100
100
100
100
100

White

+ (x100)- (x100)~ (x100)= (x100)(x100)

100
100
100
100
100

White

L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)
L1-L2-L3-N-PE (x20)
U1-U2-U3-V1-V2-V3-W1W2-W3 (x10) + U1 (x10)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White
White
White
White
White
White

White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White

Type

Part Number

Pkg

Weightcard(1 pce) g

MC812PAMC812PAMC812PAMC812PA1SNK166231R0000
1SNK166241R0000
1SNK166251R0000
1SNK166261R0000

1
1
1
1

14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK167001R0000
1SNK167011R0000
1SNK167021R0000
1SNK167031R0000
1SNK167041R0000
1SNK167051R0000
1SNK167061R0000
1SNK167071R0000
1SNK167081R0000
1SNK167091R0000

1
1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PA1SNK168001R0000
1SNK168011R0000
1SNK168021R0000
1SNK168031R0000
1SNK168041R0000

1
1
1
1
1

14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK168051R0000
1SNK168061R0000
1SNK168071R0000
1SNK168091R0000
1SNK168101R0000
1SNK168111R0000
1SNK168121R0000
1SNK168131R0000
1SNK168141R0000
1SNK168151R0000
1SNK168161R0000
1SNK168171R0000
1SNK168181R0000
1SNK169001R0000
1SNK169011R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

1SNK160010S0201 - Rev. A

8 mm 0.315 in spacing

Number ofmarkers per card

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSMC812PA terminal block markers
Pre-printed marker card for vertical terminal block assembly
Description
Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols.

Main technical data
MC812PAMaterial

Flammability

Polyamide

V2

Dimensionsmm
7.6 x 12inches
0.299 x 0.472

Ordering details

8 mm 0.315 in spacing

0->9 (x10)
1->10 (x10)
11->20 (x10)
21->30 (x10)
31->40 (x10)
41->50 (x10)
51->60 (x10)
61->70 (x10)
71->80 (x10)
81->90 (x10)
91->100 (x10)
101->110 (x10)
111->120 (x10)
121->130 (x10)
131->140 (x10)
141->150 (x10)
151->160 (x10)161->170 (x10)
171->180 (x10)
181->190 (x10)
191->200 (x10)

Number ofmarkers per card
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

Color

1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900
901->1000

100
100
100
100
100
100
100
100
100
100

White

A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

Type

Part Number

Pkg

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK160092R0000
1SNK160012R0000
1SNK160022R0000
1SNK160032R0000
1SNK160042R0000
1SNK160052R0000
1SNK160062R0000
1SNK160072R0000
1SNK160082R0000
1SNK160084R0000
1SNK160102R0000
1SNK160112R0000
1SNK160122R0000
1SNK160132R0000
1SNK160142R0000
1SNK160152R0000
1SNK160162R0000
1SNK160172R0000
1SNK160182R0000
1SNK160192R0000
1SNK160202R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

Weight
g
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK165012R0000
1SNK165022R0000
1SNK165032R0000
1SNK165042R0000
1SNK165052R0000
1SNK165062R0000
1SNK165072R0000
1SNK165082R0000
1SNK165092R0000
1SNK165102R0000

1
1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166012R0000
1SNK166022R0000
1SNK166032R0000
1SNK166042R0000
1SNK166052R0000
1SNK166062R0000
1SNK166072R0000
1SNK166082R0000
1SNK166092R0000
1SNK166102R0000
1SNK166112R0000
1SNK166122R0000
1SNK166132R0000
1SNK166142R0000
1SNK166152R0000
1SNK166162R0000
1SNK166172R0000
1SNK166182R0000
1SNK166192R0000
1SNK166202R0000
1SNK166212R0000
1SNK166222R0000

card

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

(1 pce)

1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
1
14.00
Continue on next page →PAGE 259

6

1SNK160011S0201 - Rev. A

Description

MC812PA terminal block markers
Pre-printed marker card for vertical terminal block assembly

Ordering details
Description

MC812PA

6← Continuation of previous pageW (x100)
100
X (x100)
100
Y (x100)
100
Z (x100)
100

Color

Type

Part Number

Pkg
card

White
White
White
White

0 (x100)
1 (x100)
2 (x100)
3 (x100)
4 (x100)
5 (x100)
6 (x100)
7 (x100)
8 (x100)
9 (x100)

100
100
100
100
100
100
100
100
100
100

White

+ (x100)- (x100)~ (x100)= (x100)(x100)

100
100
100
100
100

White

L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)+24V (x100)+48V (x100)-24V (x100)-48V (x100)
L1-L2-L3-N-PE (x20)
U1-U2-U3-V1-V2-V3-W1W2-W3 (x10) + U1 (x10)

100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100
100

White

White
White
White
White
White
White
White
White
White

White
White
White
White

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

Weightg(1 pce)MC812PAMC812PAMC812PAMC812PA1SNK166232R0000
1SNK166242R0000
1SNK166252R0000
1SNK166262R0000

1
1
1
1

14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK167002R0000
1SNK167012R0000
1SNK167022R0000
1SNK167032R0000
1SNK167042R0000
1SNK167052R0000
1SNK167062R0000
1SNK167072R0000
1SNK167082R0000
1SNK167092R0000

1
1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PA1SNK168002R0000
1SNK168012R0000
1SNK168022R0000
1SNK168032R0000
1SNK168042R0000

1
1
1
1
1

14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK168052R0000
1SNK168062R0000
1SNK168072R0000
1SNK168092R0000
1SNK168102R0000
1SNK168112R0000
1SNK168122R0000
1SNK168132R0000
1SNK168142R0000
1SNK168152R0000
1SNK168162R0000
1SNK168172R0000
1SNK168182R0000
1SNK168192R0000
1SNK168202R0000
1SNK168212R0000
1SNK168222R0000
1SNK169002R0000
1SNK169012R0000

1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1
1

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

1SNK160011S0201 - Rev. A

8 mm 0.315 in spacing

Number ofmarkers per card

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSUMH universal wire markers holder - MG2-TDMO clip-on blank wire marker
Markers and marking systems

UMH universal wire markers holder
Description–– Compatible with MG2 - TDMO wire markers and most of the wire markers available on the market (wiremarkers not supplied with UMH);–– Quickly put it on any SNK terminal blocks and accessories: strip mounting of 10 parts for 5.2 mm 0.205 in
spacing, unitary mounting for other spacings.

5.2 mm 0.205 in spacing

Ordering details

Mounting instructions

Description

Color

5.2 mm 0.205 in spacing

Type
Grey

Part Number

UMH

1SNK900611R0000

Pkg

Weightqty(1 pce) g

10

0.20

Main technical data
Material specifications

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Ambient temperature min/max
Install the UMH on the terminal blocks (strip
mounting) and slide on the wire markers.

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F-23 ... +104 °F

MG2-TDMO clip-on blank wire marker
Description–– Rigid Polycarbonate marker to be directly printed and snaped on the wire or the UMH wire marker holder,–– Print with support plate MG2-PTM.

1SNC160118F0014

Main technical data

MG2-TDMO

Material

Flammability

Temperature range

PC

V0-40°C ... +140°C, - 22°F ... +176°F

DimensionsmminNumber ofColormarkers per card

Type

MG2-TDMO-01
4 x 12 0.157 x 0.472
4 x 16 0.157 x 0.630
4 x 12 0.157 x 0.472
4 x 16 0.157 x 0.630

40
40
40
40

White
White
Yellow
Yellow

MG2-TDMO-01 40390
MG2-TDMO-01 40391
MG2-TDMO-01 40340
MG2-TDMO-01 40341

MG2-TDMO-02
4 x 12 0.157 x 0.472
4 x 16 0.157 x 0.630
4 x 12 0.157 x 0.472
4 x 16 0.157 x 0.630

40
40
40
40

White
White
Yellow
Yellow

MG2-TDMO-03
4 x 12 0.157 x 0.472
4 x 16 0.157 x 0.630
4 x 12 0.157 x 0.472
4 x 16 0.157 x 0.630

40
40
40
40

White
White
Yellow
Yellow

Ordering details

6Part Number

SW
code

Pkg
qty

Weight(1 pce) g

1SNB040390R0412
1SNB040391R0416
1SNB040340R0412
1SNB040341R0416

125
128
125
128

880
880
800
800

0.30
0.30
0.30
0.30

MG2-TDMO-02 40490
MG2-TDMO-02 40491
MG2-TDMO-02 40440
MG2-TDMO-02 40441

1SNB040490R0412
1SNB040491R0416
1SNB040440R0412
1SNB040441R0416

126
129
126
129

640
640
640
640

0.40
0.40
0.40
0.40

MG2-TDMO-03 40590
MG2-TDMO-03 40591
MG2-TDMO-03 40540
MG2-TDMO-03 40541

1SNB040590R0412
1SNB040591R0416
1SNB040540R0412
1SNB040541R0416

127
130
127
130

560
560
560
560

0.40
0.40
0.40
0.40

MG3 KIT 

AMS 250

Description

Support status

Support plate
Support plate for cable tags
MG2-TDMO & MG-TDM 4x16mm

Purchased separately

AMS 600
TypeHTP500Part Number

MG2-PTM 991010 1SNB991010R0000

Pkg

Weightqty(1 pce) g1

116.00MG3 KIT

PAGE 261

1SNK160083S0201 - Rev. A

Marking system

Markers for components
Markers and marking systems

1SNC160138F0014

MG-TAR markers for components
Description
Identify your terminal blocks assembly with the precut blank label adapted to the LH label holders.

Ordering details

MG-TAR
8.5
0.335"

Description

MG-TARFor LH label holder
For LH-R1 label
holder

30 1.18"

Nb. ofmarkers
per card
33
18

Nb. ofColorcard bypackage
White
50
50

Type

Part Number

SW
code

MG-TAR 45490
MG-TAR 45194

1SNB045490R8530 720
1SNB045194R1735 711

Pkg

Weightmarker

1 marker g

1650
900

0.371
0.628

Main technical data
Material specifications
17 0.669

MG-TAR

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rigid PVC
V0-30 ... +80 °C-30 ... +80 °C+10 ... +40 °C-22 ... +176 °F-22 ... +176 °F+50 ... +104 °F

35 1.378"

1SNC160139F0014

MG-TAA markers for components
Description
Identify your terminal blocks assembly with the self adhesive label adapted to the LH label holders.

Ordering details

MG-TAA

MG-TAA

For LH label holder
For LH-R1 label
holder

30 1.18"

MG-TAA

Nb. ofmarkers
per card
33
33
18
18

Nb. ofColorcard bypackageWhite
25
Yellow
25
White
25
Yellow
25

TypePart Number

SW
code

MG-TAA 49498
MG-TAA 49448
MG-TAA 49198
MG-TAA 49148

1SNB049498R8530
1SNB049448R8530
1SNB049198R1735
1SNB049148R1735

33
33
711
711

Pkg

Weightmarker

1 marker g

825
825
450
450

0.55
0.55
0.91
0.91

Main technical data
17 0.669

Material specifications
Ambient temperature
min/max

35 1.378"

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rigid PVC
V0-30 ... +80 °C-30 ... +80 °C+10 ... +40 °C-22 ... +176 °F-22 ... +176 °F+50 ... +104 °F

Marking system & accessories
Description
Thermal transfer printer

Color
Grey

Type
MG3 KITPart Number
1SNB419001R0000

Pkg

Weightqty(1 pce) g1

12600
1SNK160099S0201

6

8.5
0.335"

Description

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSMarkers for components
Markers and marking systems

1SNC160137F0014

MG-TAPW markers for components
Description
Identify your terminal blocks assembly with the precut blank label adapted to the LH label holders.

Ordering details

29 1.141"90.354"

MG-TAPW

Description

For LH label holder

Nb. ofmarkers
per card30
30

Nb. ofColorcard bypackageWhite
50
Yellow
50

TypePart Number

SW
code

MG-TAPW 49096
MG-TAPW 49046

1SNB049096R0929 363
1SNB049046R0929 363

Pkg

Weightmarker

1 marker g

1500
1500

0.30
0.30

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rigid PVC
V0-30 ... +80 °C-30 ... +80 °C+10 ... +40 °C-22 ... +176 °F-22 ... +176 °F+50 ... +104 °F

6Marking system & accessories
Description
Thermal transfer printer

Color
Grey

Type
MG3 KITPart Number
1SNB419001R0000

Pkg

Weightqty(1 pce) g1

12600
1SNK160100S0201

MG-TAPW

PAGE 263

LabelMarkers and marking systems

1SNK500098F0000

MCLH label
Description
Identify your terminal blocks assembly with the self adhesive label adapted to the LH label holders.

Ordering details

MCLH
8.8
0.346"

Description

MCLH

For LH label holder
For LH-R1 label
holder
17.65 0.695"

30 1.18"

MCLH-R1

35.35 1.39"

Nb. ofmarkers
per card
36
15

Nb. ofColorcard bypackage
White
25
25

YellowWhite
Yellow

TypePart Number

MCLH
MCLH-YLMCLH-R1
MCLH-R1-YL

1SNK900630R0000
1SNK900633R0000
1SNK900631R0000
1SNK900634R0000

SW
code

Pkg

Weightcard

1 card g

25
25
25
25

10.00
10.00
10.00
10.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

PVC + adhesive acrylic
V0-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Marking system & accessories
1

2

Description
1
2

Plotter
Support plate for AMS

Color

Type
AMS 600 KITSPRC 21

Part Number
1SNA360000R2400
1SNA360031R0600

Pkg

Weightqty(1 pce) g

1112600.00
851.00Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK160101S0201

6

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSHTP500 thermal transfer printerConsumables
Feeders and support plates
Description

Color

Type

Part Number

Pkg
qty

Universal feeder for marker cards
Support plate for TE Connectivity terminal block markers
Universal support plate for wire markers

HTP500-FEED
HTP500-PL2
HTP500-PL

1SNA235703R0400
1SNA235705R0600
1SNA235704R0500

1
1
1

Type

Part Number

Pkg

Weight(1 pce) g

HTP500-CLEAN

Accessories
Description

Color

qty

HTP500-FEEDBlack ribbon cassette
Red ribbon cassette for identification plates
and adhesive labels
Red ribbon cassette for terminal blocks
and wire markers
Cleaning cassetteStandard cleaning roll ø18
Printing head
Dust cover for HTP500 and AMS 600 systems
Wooden box for HTP500-V2 KIT
Software CD
Support table
Power supply cable

RIB-B
RIB-R

1SNA235710R0600
1SNA235711R2300

3
3

RIB-RS

1SNA235718R0200

3

HTP500-CLEAN
HTP500-ROLL
HTP500-PRINT
DUST COVER
HTP500-WB
HTS500
HTP500-BAS
HTP500-PW

1SNA235714R2600
1SNA235715R2700
1SNA235716R2000
1SNA360161R1500
1SNA235717R2100
1SNA235702R0300
1SNA235706R0700
1SNA235709R1200

1
1
1
1
1
1
1
1

Weight(1 pce) g

HTP500-PL2

6

1SNK160015S0201 - Rev. A

RIB-B

PAGE 265

MG3 thermal transfer printerKit and accessories
Description–– Versatile,–– Compact and robust,–– Easy to install and use.

Ordering details
Description
MG3 KITColor

MG3 Thermal transfer printer KIT
List of items included in the KIT:
1 MG3 Thermal transfer printer1 Software CD
1 Power supply cable
1 USB cable
1 Protective cover
1 Ribbon take up spool
1 Black monochrome ribbon
1 Support plate for cable tags MG-TPM
1 Support plate for labels, cables, plates andvarious markers
1 Support plate for terminal block markers
MG-CPM-01(5x10 and 5x15),02,03,04,07
1 Support plate for SNK series terminal block
markers (MG-CPM-13)

Type
MG3 KITPart Number
1SNB419001R0000

Pkg

Weightpce(1 pce) g

1

12600.00

MG3
MG3 SOFTWARE
MG3 POWER
MG3 USB
MG2 COVE 991680
MG2-CRB 991654
MG2-ETR 991600
MG2-PWC 991000
MG2-PLT 991002
MG2-QTB 991011
MG2-ETB 991016

Support plates
Description

Color

Type

Part Number

Pkg
pce

Support plate MG2-...
6

Support template for:
Cable tags MG-TPM
Labels, cable tags, plates and various markers
Terminal block markers MG-CPM-05,12
Terminal block markers MG-CPM-06
Terminal block markers MG-CPM-10
Cable tags MG-TDM (4x12 mm)
Terminal block markers MG-CPM-01 (5x7 mm)
Cable tags MG2-TDMO and MG-TDM (4x16 mm)
Terminal block markers MG-CPM-01(5x10 and 5x15 mm),02,03,04,07
Terminal block markers TE Connectivity RC andMC series
Terminal block markers MG-CPM-09
Terminal block markers SNK series MG-CPM-13

Weightg(1 pce)MG2-PWC 991000
MG2-PLT 991002
MG2-WTB 991004
MG2-STB 991005
MG2-CTB 991006
MG2-PTD 991007
MG2-MTB 991008
MG2-PTM 991010
MG2-QTB 991011

1SNB991000R0000
1SNB991002R0000
1SNB991004R0000
1SNB991005R0000
1SNB991006R0000
1SNB991007R0000
1SNB991008R0000
1SNB991010R0000
1SNB991011R0000

1
1
1
1
1
1
1
1
1

148.00148.00151.00158.00156.00126.00149.00116.00120.00MG2-ABM 991012

1SNB991012R0000

1

146.00

MG2-LTB 991013
MG2-ETB 991016

1SNB991013R0000
1SNB991016R0000

1
1

128.00100.00TypePart Number

PET blank cover for support plate
Description

Color

Pkg
pce

PET blank for support plate MG2-PWC
PET blank for support plate MG2-PLT
PET blank for support plate MG2-PTD
PET blank for support plate MG2-MTB
PET blank for support plate MG2-WTB
PET blank for support plate MG2-STB
PET blank for support plate MG2-CTB
PET blank for support plate MG2-QTB
PET blank for support plate MG2-ETB

MG2-TWC 991502
MG2-TLT 991522
MG2-TTD 991563
MG2-TMT 991513
MG2-TWT 991542
MG2-TST 991552
MG2-TCT 991562
MG2-TGT 991532
MG2-TTB 991512

1SNB991502R0000
1SNB991522R0000
1SNB991563R0000
1SNB991513R0000
1SNB991542R0000
1SNB991552R0000
1SNB991562R0000
1SNB991532R0000
1SNB991512R0000

3
3
3
3
3
3
3
3
3

Type

Part Number

Pkg

Weight
g
16.70
14.70
11.70
12.00
12.00
21.50
12.00
11.70
10.70

(1 pce)Accessories
Color

pce

Print head cleaning kit
Black monochrome ribbon
Blue monochrome ribbon
Red monochrome ribbon
Green monochrome ribbon
White monochrome ribbon
Ribbons MG2-ETR...

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Black
Blue
Red
Green
White

MG2-CKP 991670
MG2-ETR 991600
MG2-ETR 991601
MG2-ETR 991602
MG2-ETR 991603
MG2-ETR 991606

1SNB991670R0000
1SNB991600R0000
1SNB991601R0000
1SNB991602R0000
1SNB991603R0000
1SNB991606R0000

1
1
1
1
1
1

Weightg
336.00227.00229.00
255.00247.00333.00(1 pce)1SNC160112S0201 - Rev. A

Description

AMS plotter
Kit and accessories

AMS 600
Description–– For basic marking applications,–– Economic,–– Full-size format,–– Print original manufacturers' markers.
AMS 600

Ordering details
Description

Color

AMS 600 Plotter KIT
List of items included in the KIT:
1 AMS 600 plotter pen printer1 Software CD
1 Power supply cable
1 USB cable
1 Support plate for RC / MC / RCTT / WMTT /BA4 / RCT
1 Support plate for MC...PA
1 Plotter pen Ø 0.25 mm .01 in
1 Plotter pen Ø 0.35 mm .014 in
5 Ink cartridges
1 Cleaner fluid
1 Cleaner kit

Type
AMS 600 KIT

Part Number
1SNA360000R2400

Pkg

Weightpce(1 pce) g

1

12600

AMS 600AMS SOFTWAREAMS POWERAMS USB
SPRC1
SPRC 30-3
AMS PEN 0.25
AMS PEN 0.35
AMS INK CARTRIDGESAMS CLEANER FLUIDAMS CLEANER KIT

AMS 250
Description–– Basic needs,–– Economic,–– Half-size format–– Compatible with most of AMS 600 accessories.
6

Ordering details
Description
AMS 250 Plotter KIT
List of items included in the KIT:
1 AMS 250 plotter pen printer1 Software CD
1 Power supply cable
1 USB cable
1 Support plate for BA4 / MC / RC / RCAL /RCT / RCTT
1 Disposable plotter penØ 0.25 mm .01 in EDR ink
1 Disposable plotter penØ 0.35 mm .014 in EDR ink

Color

Type
AMS 250 BASIC KITPart Number
1SNA360000R2500

Pkg

Weightpce(1 pce) g

1

8800

AMS 250 BASICAMS SOFTWAREAMS POWERAMS USBSPRC2DISPOSABLE AMS PEN
ED-R 0.25
DISPOSABLE AMS PEN
ED-R 0.35

1SNC160110S0201

AMS 250

PAGE 267

AMS plotter
Kit and accessories
Support plates for TE Connectivity markers
Description

Compatibility
AMS 500
AMS 600

Type

Pkg

Weightpce(1 pce)

1SNA360010R1500
1SNA360011R1500
1SNA360014R0500
1SNA360015R0600
1SNA360023R0600
1SNA360024R0700
1SNA360025R0000
1SNA360026R0100
1SNA360036R0300
1SNA360037R0400
1SNA360040R2300
1SNA360038R1500
1SNA360039R1700
1SNA360031R0600

1
1
1
1
1
1
1
1
1
1
1
1
1
1

1500.00
600.00300.001700.00
260.00300.00300.00300.00300.00300.00300.00300.00500.00500.00Part Number

Pkg

Weightpce(1 pce)Part Number

AMS 250g

Support plates for:

SPRC1

RC/MC/RCTT/WMTT/BA4/RCT full format
RC/MC/RCTT/WMTT/BA4/RCTRB strips
RTM7-9PIB
BA5-50
RC-X10A
2 RC cards
WM markers
PAM strip
RPCV markers
RCL, P, W510
MC... PA

A4 universal support plate
SPRC2




























SPRC 1SPRC 2SPRC 4SPRC 5SPRC 13SPRC 14SPRC 15SPRC 16SPRC 26
SPRC 27
SPRC 28
SPRC 29
SPRC 30-3
SPRC 21

Support plates for other manufacturers
Description
Support plates for markers:
WielandWeidmüller
Phoenix ZBM 5/6
Phoenix ZB
Allen Bradley WRZ
Wago mini WSB5

Compatibility
AMS 500
AMS 600

AMS 250















Type

SPRC 6SPRC 7SPRC 8SPRC 9SPRC 10SPRC 11

1SNA360016R0700
1SNA360017R0000
1SNA360018R1100
1SNA360019R1200
1SNA360020R1700
1SNA360021R0400

TypePart Number

1
1
1
1
1
1

g

350.00400.00300.00300.00330.00300.00

SPRC30-3

Accessories

6

AMS PENAMS CLEANER KIT

Diameter
Color

Plotter pen P 2.0 black ink Ø 0.18 mm 0.007 inØ 0.25 mm 0.01 inØ 0.35 mm 0.014 inØ 0.50 mm 0.02 inØ 0.70 mm 0.028 inØ 1.00 mm 0.039 in
Disposable plotter penØ 0.25 mm 0.01 in
P 2.0 black ink
Ø 0.35 mm 0.014 in
Disposable plotter penØ 0.18 mm 0.007 in
ED-R black ink
Ø 0.25 mm 0.01 in

OrangeØ 0.35 mm 0.014 inYellow

5 ink cartridges 1 ml
2 cleaner fluid bottles, 2x10 ml
Cleaner kit including: 1 rinse bottle and 1 blotting paper
Dust coverService kit for pen maintenanceSelf-adhesive support for support plate SPRC 1
Plotter head for AMS 600 including 1 printing
module, 1 pen holder and 1 dust cover

AMS INK CARTRIDGES

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Red
White
Yellow
Brown
Blue
White
Yellow
Red
White

Pkg
1
1
1
1
1
1
1
1
1

Weight
g
15.00
15.00
15.00
26.00
26.00
26.00
24.00
24.00
24.00

1

24.00

1

24.00

1
1
1
1
1
1
1

18.00
40.00
34.00
200.00
12.00
70.00
85.00

pce

AMS PEN 0.18
1SNA360103R1400
AMS PEN 0.25
1SNA360100R2500
AMS PEN 0.35
1SNA360101R1200
AMS PEN 0.50
1SNA360104R1500
AMS PEN 0.70
1SNA360105R1600
AMS PEN 1.00
1SNA360106R1700
DISPOSABLE AMS PEN 0.25 1SNA360120R1000DISPOSABLE AMS PEN 0.35 1SNA360121R0500
DISPOSABLE AMS PEN
1SNA360124R1000
ED-R 0.18
DISPOSABLE AMS PEN
1SNA360122R1000
ED-R 0.25
DISPOSABLE AMS PEN
1SNA360123R0500
ED-R 0.35
AMS INK CARTRIDGES
1SNA360150R2600
AMS CLEANER FLUID
1SNA360155R1700
AMS CLEANER KIT
1SNA360156R1000
DUST COVER
1SNA360161R1500
SERVICE KIT FOR AMS 600 1SNA360162R1600
SPDST1
1SNA360163R1700
PEN HOLDER
1SNA360098R1200(1 pce)1SNC160111S0201 - Rev. A

Description

PB-217

6

PAGE 269

7Part Number

Type

1SNA113542R1000
1SNA113544R1200
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA164800R0300
1SNA168500R1200
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA168700R2200
1SNA173220R0500
1SNA173523R1100
1SNA174300R1700
1SNA178430R0500
1SNA178431R2200
1SNA178529R0400
1SNA179371R1600
1SNA179726R0200
1SNA206053R0700
1SNA206054R0000
1SNA206126R2500
1SNA206223R0600
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206721R0100
1SNA206765R0000
1SNA206772R0000
1SNA206782R0000
1SNA235106R2600
1SNA235155R2600
1SNA235157R2000
1SNA235158R0100
1SNA235159R0200
1SNA235702R0300
1SNA235703R0400
1SNA235704R0500
1SNA235705R0600
1SNA235706R0700
1SNA235709R1200
1SNA235710R0600
1SNA235711R2300
1SNA235714R2600
1SNA235715R2700
1SNA235716R2000
1SNA235717R2100
1SNA235718R0200
1SNA238000R1600
1SNA360000R2400
1SNA360000R2500
1SNA360010R1500
1SNA360011R1500
1SNA360014R0500
1SNA360015R0600
1SNA360016R0700
1SNA360017R0000
1SNA360018R1100
1SNA360019R1200
1SNA360020R1700
1SNA360021R0400
1SNA360023R0600
1SNA360024R0700
1SNA360025R0000
1SNA360026R0100
1SNA360031R0600
1SNA360036R0300
1SNA360037R0400
1SNA360038R1500
1SNA360039R1700
1SNA360040R2300
1SNA360098R1200
1SNA360100R2500
1SNA360101R1200
1SNA360103R1400
1SNA360104R1500
1SNA360105R1600
1SNA360106R1700
1SNA360120R1000
1SNA360121R0500
1SNA360122R1000
1SNA360123R0500
1SNA360124R1000
1SNA360150R2600
1SNA360155R1700

PC5-2
105
PC5-10
105
PC8-2
226
PC8-3
226
PC8-4
226
PC8-10155
PR3.G2
197
PR4
198
TGA8
120
TGA8
120
TGA8
120
ANT
120
PR5
198
PR30
196
PC81-10120
PR3.Z2
196
RCPEB
201
EPR1
201
PR50
197
CN5
120
AJS9
152
BJMI31.2
91
BJMI31.3
91
BJMI36.2
92
BJMI36.3
92
AJS9-BK
154
AJS9-GN
154
AJS9-GR154
AJS9-BL154
AJS9-RD
154
AL4-M3
152
AJS9-WH
154
AJS9-PR154
AJS9-BR154
PAM43020
230
PIB2-TT
201
PIB2-TT-YL
201
RCPEAD-TT
201
RCPEAD-TT-YL
201
HTS500265
HTP500-FEED265
HTP500-PL
265
HTP500-PL2
265
HTP500-BAS
265
HTP500-PW
265
RIB-B
265
RIB-R
265
HTP500-CLEAN
265
HTP500-ROLL
265
HTP500-PRINT265
HTP500-WB
265
RIB-RS265
RC101091
AMS 600 KIT
245
AMS 250 BASIC KIT
267
SPRC 1
268
SPRC 2268
SPRC 4
268
SPRC 5
268
SPRC 6268
SPRC 7268
SPRC 8268
SPRC 9268
SPRC 10268
SPRC 11
268
SPRC 13
268
SPRC 14268
SPRC 15
268
SPRC 16
268
SPRC 21264
SPRC 26
268
SPRC 27
268
SPRC 29
268
SPRC 30-3
245
SPRC 28268
PEN HOLDER
268
AMS PEN 0.25
268
AMS PEN 0.35
268
AMS PEN 0.18
268
AMS PEN 0.50
268
AMS PEN 0.70
268
AMS PEN 1.00
268
DISPOSABLE AMS PEN 0.25 268
DISPOSABLE AMS PEN 0.35 268
DISPOSABLE AMS PEN ED-R 0.25 268
DISPOSABLE AMS PEN ED-R 0.35 268
DISPOSABLE AMS PEN ED-R 0.18 268
AMS INK CARTRIDGES
268
AMS CLEANER FLUID
268

Page

Part Number

Type

Page

Part Number

Type

Page

1SNA360156R1000
1SNA360161R1500
1SNA360162R1600
1SNA360163R1700
1SNA399726R0700
1SNA399787R0500
1SNA399788R1600
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400842R0000
1SNA400843R0000
1SNA400849R0000
1SNA400850R0000
1SNB040340R0412
1SNB040341R0416
1SNB040390R0412
1SNB040391R0416
1SNB040440R0412
1SNB040441R0416
1SNB040490R0412
1SNB040491R0416
1SNB040540R0412
1SNB040541R0416
1SNB040590R0412
1SNB040591R0416
1SNB041740R0512
1SNB041741R0612
1SNB041790R0512
1SNB041791R0612
1SNB043196R0012
1SNB045194R1735
1SNB045490R8530
1SNB046415R0615
1SNB046915R0615
1SNB049046R0929
1SNB049096R0929
1SNB049148R1735
1SNB049198R1735
1SNB049448R8530
1SNB049498R8530
1SNB419001R0000
1SNB991000R0000
1SNB991002R0000
1SNB991004R0000
1SNB991005R0000
1SNB991006R0000
1SNB991007R0000
1SNB991008R0000
1SNB991010R0000
1SNB991011R0000
1SNB991012R0000
1SNB991013R0000
1SNB991016R0000
1SNB991502R0000
1SNB991512R0000
1SNB991513R0000
1SNB991522R0000
1SNB991532R0000
1SNB991542R0000
1SNB991552R0000
1SNB991562R0000
1SNB991563R0000
1SNB991600R0000
1SNB991601R0000
1SNB991602R0000
1SNB991603R0000
1SNB991606R0000
1SNB991670R0000
1SNK140000R0000
1SNK140004R0000
1SNK140011R0000
1SNK140012R0000
1SNK140021R0000
1SNK140022R0000
1SNK140031R0000
1SNK140032R0000
1SNK140041R0000
1SNK140042R0000
1SNK140051R0000
1SNK140052R0000
1SNK140061R0000
1SNK140062R0000
1SNK140071R0000
1SNK140072R0000
1SNK140081R0000
1SNK140082R0000
1SNK140083R0000

AMS CLEANER KIT
DUST COVER
SERVICE KIT FOR AMS 500
SPDST1
EPR2
CPBP2
CPBP1
PC8-R1
PC8-R2
PC8-R3
PC8-R4
PC8-R5
PC8-R6
PC8-R7PC8-R8
MG2-TDMO-01 40340
MG2-TDMO-01 40341
MG2-TDMO-01 40390
MG2-TDMO-01 40391
MG2-TDMO-02 40440
MG2-TDMO-02 40441
MG2-TDMO-02 40490
MG2-TDMO-02 40491
MG2-TDMO-03 40540
MG2-TDMO-03 40541
MG2-TDMO-03 40590
MG2-TDMO-03 40591
MG-CPM 13 41740
MG-CPM 13 41741
MG-CPM 13 41790
MG-CPM 13 41791
MG-CPMFA 43196
MG-TAR 45194
MG-TAR 45490
MG-VYT 46415
MG-VYT 46915
MG-TAPW 49046
MG-TAPW 49096
MG-TAA 49148
MG-TAA 49198
MG-TAA 49448
MG-TAA 49498
MG3 KIT
MG2-PWC 991000
MG2-PLT 991002
MG2-WTB 991004
MG2-STB 991005
MG2-CTB 991006
MG2-PTD 991007
MG2-MTB 991008
MG2-PTM 991010
MG2-QTB 991011
MG2-ABM 991012
MG2-LTB 991013
MG2-ETB 991016
MG2-TWC 991502
MG2-TTB 991512
MG2-TMT 991513
MG2-TLT 991522
MG2-TGT 991532
MG2-TWT 991542
MG2-TST 991552
MG2-TCT 991562
MG2-TTD 991563
MG2-ETR 991600
MG2-ETR 991601
MG2-ETR 991602
MG2-ETR 991603
MG2-ETR 991606
MG2-CKP 991670
MC512
MC512-YL
MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA

268
265
268
268
201
92
91
153
155
155
155
155
155
155
155
261
261
261
261
261
261
261
261
261
261
261
261
244
250
21
30
185
201
201
217
217
263
263
201
201
201
201
244
266
266
266
266
266
266
266
261
266
266
266
244
266
266
266
266
266
266
266
266
266
266
266
266
266
266
266
21
244
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246

1SNK140084R0000
1SNK140091R0000
1SNK140092R0000
1SNK140101R0000
1SNK140102R0000
1SNK140111R0000
1SNK140112R0000
1SNK140121R0000
1SNK140122R0000
1SNK140131R0000
1SNK140132R0000
1SNK140141R0000
1SNK140142R0000
1SNK140151R0000
1SNK140152R0000
1SNK140161R0000
1SNK140162R0000
1SNK140171R0000
1SNK140172R0000
1SNK140181R0000
1SNK140182R0000
1SNK140191R0000
1SNK140192R0000
1SNK140201R0000
1SNK140202R0000
1SNK145011R0000
1SNK145012R0000
1SNK145021R0000
1SNK145022R0000
1SNK145031R0000
1SNK145032R0000
1SNK145041R0000
1SNK145042R0000
1SNK145051R0000
1SNK145052R0000
1SNK145061R0000
1SNK145062R0000
1SNK145071R0000
1SNK145072R0000
1SNK145081R0000
1SNK145082R0000
1SNK145091R0000
1SNK145092R0000
1SNK145102R0000
1SNK146011R0000
1SNK146012R0000
1SNK146021R0000
1SNK146022R0000
1SNK146031R0000
1SNK146032R0000
1SNK146041R0000
1SNK146042R0000
1SNK146051R0000
1SNK146052R0000
1SNK146061R0000
1SNK146062R0000
1SNK146071R0000
1SNK146072R0000
1SNK146081R0000
1SNK146082R0000
1SNK146091R0000
1SNK146092R0000
1SNK146101R0000
1SNK146102R0000
1SNK146111R0000
1SNK146112R0000
1SNK146121R0000
1SNK146122R0000
1SNK146131R0000
1SNK146132R0000
1SNK146141R0000
1SNK146142R0000
1SNK146151R0000
1SNK146152R0000
1SNK146161R0000
1SNK146162R0000
1SNK146171R0000
1SNK146172R0000
1SNK146181R0000
1SNK146182R0000
1SNK146191R0000
1SNK146192R0000
1SNK146201R0000
1SNK146202R0000
1SNK146211R0000
1SNK146212R0000
1SNK146221R0000
1SNK146222R0000
1SNK146231R0000

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA

248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Index_1SNK160027C0206

Index
Part Number classification

IndexPart Number classification
Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNK146232R0000
1SNK146241R0000
1SNK146242R0000
1SNK146251R0000
1SNK146252R0000
1SNK146261R0000
1SNK146262R0000
1SNK147001R0000
1SNK147002R0000
1SNK147011R0000
1SNK147012R0000
1SNK147021R0000
1SNK147022R0000
1SNK147031R0000
1SNK147032R0000
1SNK147041R0000
1SNK147042R0000
1SNK147051R0000
1SNK147052R0000
1SNK147061R0000
1SNK147062R0000
1SNK147071R0000
1SNK147072R0000
1SNK147081R0000
1SNK147082R0000
1SNK147091R0000
1SNK147092R0000
1SNK148001R0000
1SNK148002R0000
1SNK148011R0000
1SNK148012R0000
1SNK148021R0000
1SNK148022R0000
1SNK148031R0000
1SNK148032R0000
1SNK148041R0000
1SNK148042R0000
1SNK148051R0000
1SNK148052R0000
1SNK148061R0000
1SNK148062R0000
1SNK148071R0000
1SNK148072R0000
1SNK148091R0000
1SNK148092R0000
1SNK148101R0000
1SNK148102R0000
1SNK148111R0000
1SNK148112R0000
1SNK148121R0000
1SNK148122R0000
1SNK148131R0000
1SNK148132R0000
1SNK148141R0000
1SNK148142R0000
1SNK148151R0000
1SNK148152R0000
1SNK148161R0000
1SNK148162R0000
1SNK148171R0000
1SNK148172R0000
1SNK148181R0000
1SNK148182R0000
1SNK148192R0000
1SNK148202R0000
1SNK148212R0000
1SNK148222R0000
1SNK149001R0000
1SNK149002R0000
1SNK149011R0000
1SNK149012R0000
1SNK149999R0000
1SNK150000R0000
1SNK150004R0000
1SNK150011R0000
1SNK150012R0000
1SNK150021R0000
1SNK150022R0000
1SNK150031R0000
1SNK150032R0000
1SNK150041R0000
1SNK150042R0000
1SNK150051R0000
1SNK150052R0000
1SNK150061R0000
1SNK150062R0000
1SNK150071R0000
1SNK150072R0000
1SNK150081R0000

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA
MC612
MC612-YL
MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA

249
246
249
246
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
249
249
249
249
247
249
247
249
21
24
250
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252

1SNK150082R0000
1SNK150083R0000
1SNK150084R0000
1SNK150091R0000
1SNK150092R0000
1SNK150101R0000
1SNK150102R0000
1SNK150111R0000
1SNK150112R0000
1SNK150121R0000
1SNK150122R0000
1SNK150131R0000
1SNK150132R0000
1SNK150141R0000
1SNK150142R0000
1SNK150151R0000
1SNK150152R0000
1SNK150161R0000
1SNK150162R0000
1SNK150171R0000
1SNK150172R0000
1SNK150181R0000
1SNK150182R0000
1SNK150191R0000
1SNK150192R0000
1SNK150201R0000
1SNK150202R0000
1SNK155011R0000
1SNK155012R0000
1SNK155021R0000
1SNK155022R0000
1SNK155031R0000
1SNK155032R0000
1SNK155041R0000
1SNK155042R0000
1SNK155051R0000
1SNK155052R0000
1SNK155061R0000
1SNK155062R0000
1SNK155071R0000
1SNK155072R0000
1SNK155081R0000
1SNK155082R0000
1SNK155091R0000
1SNK155092R0000
1SNK155102R0000
1SNK156011R0000
1SNK156012R0000
1SNK156021R0000
1SNK156022R0000
1SNK156031R0000
1SNK156032R0000
1SNK156041R0000
1SNK156042R0000
1SNK156051R0000
1SNK156052R0000
1SNK156061R0000
1SNK156062R0000
1SNK156071R0000
1SNK156072R0000
1SNK156081R0000
1SNK156082R0000
1SNK156091R0000
1SNK156092R0000
1SNK156101R0000
1SNK156102R0000
1SNK156111R0000
1SNK156112R0000
1SNK156121R0000
1SNK156122R0000
1SNK156131R0000
1SNK156132R0000
1SNK156141R0000
1SNK156142R0000
1SNK156151R0000
1SNK156152R0000
1SNK156161R0000
1SNK156162R0000
1SNK156171R0000
1SNK156172R0000
1SNK156181R0000
1SNK156182R0000
1SNK156191R0000
1SNK156192R0000
1SNK156201R0000
1SNK156202R0000
1SNK156211R0000
1SNK156212R0000
1SNK156221R0000

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA

254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252

1SNK156222R0000
1SNK156231R0000
1SNK156232R0000
1SNK156241R0000
1SNK156242R0000
1SNK156251R0000
1SNK156252R0000
1SNK156261R0000
1SNK156262R0000
1SNK157001R0000
1SNK157002R0000
1SNK157011R0000
1SNK157012R0000
1SNK157021R0000
1SNK157022R0000
1SNK157031R0000
1SNK157032R0000
1SNK157041R0000
1SNK157042R0000
1SNK157051R0000
1SNK157052R0000
1SNK157061R0000
1SNK157062R0000
1SNK157071R0000
1SNK157072R0000
1SNK157081R0000
1SNK157082R0000
1SNK157091R0000
1SNK157092R0000
1SNK158001R0000
1SNK158002R0000
1SNK158011R0000
1SNK158012R0000
1SNK158021R0000
1SNK158022R0000
1SNK158031R0000
1SNK158032R0000
1SNK158041R0000
1SNK158042R0000
1SNK158051R0000
1SNK158052R0000
1SNK158061R0000
1SNK158062R0000
1SNK158071R0000
1SNK158072R0000
1SNK158091R0000
1SNK158092R0000
1SNK158101R0000
1SNK158102R0000
1SNK158111R0000
1SNK158112R0000
1SNK158121R0000
1SNK158122R0000
1SNK158131R0000
1SNK158132R0000
1SNK158141R0000
1SNK158142R0000
1SNK158151R0000
1SNK158152R0000
1SNK158161R0000
1SNK158162R0000
1SNK158171R0000
1SNK158172R0000
1SNK158181R0000
1SNK158182R0000
1SNK158192R0000
1SNK158202R0000
1SNK158212R0000
1SNK158222R0000
1SNK159001R0000
1SNK159002R0000
1SNK159011R0000
1SNK159012R0000
1SNK159999R0000
1SNK160000R0000
1SNK160004R0000
1SNK160011R0000
1SNK160012R0000
1SNK160021R0000
1SNK160022R0000
1SNK160031R0000
1SNK160032R0000
1SNK160041R0000
1SNK160042R0000
1SNK160051R0000
1SNK160052R0000
1SNK160061R0000
1SNK160062R0000
1SNK160071R0000

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA
MC812
MC812-YL
MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA

254
252
254
253
254
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
255
255
255
255
253
255
253
255
24
30
256
257
259
257
259
257
259
257
259
257
259
257
259
257

PAGE 271

7

Index_1SNK160027C0206

Part Number

7Part Number

Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNK160072R0000
1SNK160081R0000
1SNK160082R0000
1SNK160083R0000
1SNK160084R0000
1SNK160091R0000
1SNK160092R0000
1SNK160101R0000
1SNK160102R0000
1SNK160111R0000
1SNK160112R0000
1SNK160121R0000
1SNK160122R0000
1SNK160131R0000
1SNK160132R0000
1SNK160141R0000
1SNK160142R0000
1SNK160151R0000
1SNK160152R0000
1SNK160161R0000
1SNK160162R0000
1SNK160171R0000
1SNK160172R0000
1SNK160181R0000
1SNK160182R0000
1SNK160191R0000
1SNK160192R0000
1SNK160201R0000
1SNK160202R0000
1SNK165011R0000
1SNK165012R0000
1SNK165021R0000
1SNK165022R0000
1SNK165031R0000
1SNK165032R0000
1SNK165041R0000
1SNK165042R0000
1SNK165051R0000
1SNK165052R0000
1SNK165061R0000
1SNK165062R0000
1SNK165071R0000
1SNK165072R0000
1SNK165081R0000
1SNK165082R0000
1SNK165091R0000
1SNK165092R0000
1SNK165102R0000
1SNK166011R0000
1SNK166012R0000
1SNK166021R0000
1SNK166022R0000
1SNK166031R0000
1SNK166032R0000
1SNK166041R0000
1SNK166042R0000
1SNK166051R0000
1SNK166052R0000
1SNK166061R0000
1SNK166062R0000
1SNK166071R0000
1SNK166072R0000
1SNK166081R0000
1SNK166082R0000
1SNK166091R0000
1SNK166092R0000
1SNK166101R0000
1SNK166102R0000
1SNK166111R0000
1SNK166112R0000
1SNK166121R0000
1SNK166122R0000
1SNK166131R0000
1SNK166132R0000
1SNK166141R0000
1SNK166142R0000
1SNK166151R0000
1SNK166152R0000
1SNK166161R0000
1SNK166162R0000
1SNK166171R0000
1SNK166172R0000
1SNK166181R0000
1SNK166182R0000
1SNK166191R0000
1SNK166192R0000
1SNK166201R0000
1SNK166202R0000
1SNK166211R0000

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA

259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257

1SNK166212R0000
1SNK166221R0000
1SNK166222R0000
1SNK166231R0000
1SNK166232R0000
1SNK166241R0000
1SNK166242R0000
1SNK166251R0000
1SNK166252R0000
1SNK166261R0000
1SNK166262R0000
1SNK167001R0000
1SNK167002R0000
1SNK167011R0000
1SNK167012R0000
1SNK167021R0000
1SNK167022R0000
1SNK167031R0000
1SNK167032R0000
1SNK167041R0000
1SNK167042R0000
1SNK167051R0000
1SNK167052R0000
1SNK167061R0000
1SNK167062R0000
1SNK167071R0000
1SNK167072R0000
1SNK167081R0000
1SNK167082R0000
1SNK167091R0000
1SNK167092R0000
1SNK168001R0000
1SNK168002R0000
1SNK168011R0000
1SNK168012R0000
1SNK168021R0000
1SNK168022R0000
1SNK168031R0000
1SNK168032R0000
1SNK168041R0000
1SNK168042R0000
1SNK168051R0000
1SNK168052R0000
1SNK168061R0000
1SNK168062R0000
1SNK168071R0000
1SNK168072R0000
1SNK168091R0000
1SNK168092R0000
1SNK168101R0000
1SNK168102R0000
1SNK168111R0000
1SNK168112R0000
1SNK168121R0000
1SNK168122R0000
1SNK168131R0000
1SNK168132R0000
1SNK168141R0000
1SNK168142R0000
1SNK168151R0000
1SNK168152R0000
1SNK168161R0000
1SNK168162R0000
1SNK168171R0000
1SNK168172R0000
1SNK168181R0000
1SNK168182R0000
1SNK168192R0000
1SNK168202R0000
1SNK168212R0000
1SNK168222R0000
1SNK169001R0000
1SNK169002R0000
1SNK169011R0000
1SNK169012R0000
1SNK169999R0000
1SNK505010R0000
1SNK505020R0000
1SNK505030R0000
1SNK505060R0000
1SNK505061R0000
1SNK505062R0000
1SNK505063R0000
1SNK505064R0000
1SNK505065R0000
1SNK505066R0000
1SNK505150R0000
1SNK505210R0000
1SNK505211R0000

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAZS4
ZS4-BLZS4-ORZS4-YLZS4-GNZS4-RDZS4-PRZS4-BRZS4-WHZS4-BK
ZS4-PEZS4-D2ZS4-D1

259
257
259
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
260
260
260
260
258
260
258
260
30
80
80
80
80
80
80
80
80
80
80
80
136
137

1SNK505212R0000
1SNK505214R0000
1SNK505215R0000
1SNK505220R0000
1SNK505230R0000
1SNK505310R0000
1SNK505311R0000
1SNK505312R0000
1SNK505313R0000
1SNK505314R0000
1SNK505315R0000
1SNK505316R0000
1SNK505320R0000
1SNK505321R0000
1SNK505330R0000
1SNK505331R0000
1SNK505910R0000
1SNK505911R0000
1SNK505912R0000
1SNK505960R0000
1SNK505961R0000
1SNK506010R0000
1SNK506011R0000
1SNK506012R0000
1SNK506013R0000
1SNK506020R0000
1SNK506021R0000
1SNK506022R0000
1SNK506030R0000
1SNK506060R0000
1SNK506061R0000
1SNK506062R0000
1SNK506063R0000
1SNK506064R0000
1SNK506065R0000
1SNK506066R0000
1SNK506067R0000
1SNK506068R0000
1SNK506150R0000
1SNK506151R0000
1SNK506152R0000
1SNK506153R0000
1SNK506210R0000
1SNK506211R0000
1SNK506212R0000
1SNK506213R0000
1SNK506214R0000
1SNK506220R0000
1SNK506230R0000
1SNK506250R0000
1SNK506260R0000
1SNK506262R0000
1SNK506265R0000
1SNK506266R0000
1SNK506310R0000
1SNK506311R0000
1SNK506312R0000
1SNK506313R0000
1SNK506314R0000
1SNK506315R0000
1SNK506316R0000
1SNK506320R0000
1SNK506321R0000
1SNK506322R0000
1SNK506330R0000
1SNK506331R0000
1SNK506410R0000
1SNK506411R0000
1SNK506412R0000
1SNK506413R0000
1SNK506414R0000
1SNK506415R0000
1SNK506416R0000
1SNK508010R0000
1SNK508011R0000
1SNK508013R0000
1SNK508020R0000
1SNK508030R0000
1SNK508060R0000
1SNK508061R0000
1SNK508062R0000
1SNK508063R0000
1SNK508064R0000
1SNK508065R0000
1SNK508066R0000
1SNK508150R0000
1SNK508151R0000
1SNK508310R0000
1SNK508311R0000

ZS4-T3ZS4-D-CH-UD
ZS4-D-CH-DU
ZS4-D2-BL
ZS4-D2-OR
ZS4-S
ZS4-S-T2ZS4-S-T2.3
ZS4-SPZS4-SP-T2
ZS4-D2-S
ZS4-D2-S-T2
ZS4-S-BLZS4-S-T2-BL
ZS4-S-ORZS4-S-T2-OR
ES4
ES6-4S
ES6-3S
ES4-D2
ES4-T3
ZS6
ZS6-3S
ZS6-4SZS4-R2ZS6-BLZS6-3S-BL
ZS6-4S-BL
ZS6-ORZS6-YLZS6-GNZS6-RDZS6-PRZS6-BRZS6-WHZS6-BK
ZS6-3S-YL
ZS6-4S-YL
ZS6-PE
ZS6-3S-PE
ZS6-4S-PE
ZS4-PE-R2
ZS6-D2ZS6-D1ZS6-D2-PE
ZS4-T3-R1
ZS6-D1-RD
ZS6-D2-BL
ZS6-D2-OR
ZS6-D1-PE
ZS6-D2-YL
ZS6-D2-RD
ZS6-D2-WH
ZS6-D2-BK
ZS4-S-R1
ZS4-S-T2-R1
ZS4-S-T2.3-R1
ZS4-SP-R1
ZS4-SP-T2-R1
ZS6-S
ZS6-S-4S-T2ZS4-S-R1-BL
ZS4-S-T2-R1-BL
ZS6-S-BLZS4-S-R1-OR
ZS4-S-T2-R1-OR
ZS4-SFZS4-SF-T2
ZS4-SF-R1
ZS4-SF-R2
ZS4-S-R2ZS4-SF-R3
ZS4-SF-R4
ZS10
ZS10-R1ZS4-R1
ZS10-BL
ZS10-ORZS10-YL
ZS10-GN
ZS10-RD
ZS10-PR
ZS10-BR
ZS10-WH
ZS10-BK
ZS10-PE
ZS10-PE-R1
ZS10-ST
ZS10-ST-T4

146
148
149
136
136
105
106
106
112
113
142
143
105
106
105
106
80
83
82
136
146
81
82
83
130
81
82
83
81
81
81
81
81
81
81
81
82
83
81
82
83
131
138
139
140
147
139
138
138
138
138
138
138
138
107
108
108
114
115
109
110
107
108
109
107
108
126
127
128
129
132
128
129
84
152
124
84
84
84
84
84
84
84
84
84
84
153
154
152

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

Index_1SNK160027C0206

Index
Part Number classification

IndexPart Number classification
Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNK508312R0000
1SNK508315R0000
1SNK508316R0000
1SNK508320R0000
1SNK508410R0000
1SNK508411R0000
1SNK508412R0000
1SNK508413R0000
1SNK508414R0000
1SNK508415R0000
1SNK508416R0000
1SNK508417R0000
1SNK508418R0000
1SNK508419R0000
1SNK508421R0000
1SNK508422R0000
1SNK508423R0000
1SNK508424R0000
1SNK508425R0000
1SNK508430R0000
1SNK508910R0000
1SNK508911R0000
1SNK508960R0000
1SNK510010R0000
1SNK510020R0000
1SNK510030R0000
1SNK510150R0000
1SNK512010R0000
1SNK512020R0000
1SNK512060R0000
1SNK512150R0000
1SNK516010R0000
1SNK516011R0000
1SNK516020R0000
1SNK516021R0000
1SNK516030R0000
1SNK516060R0000
1SNK516063R0000
1SNK516064R0000
1SNK516150R0000
1SNK516151R0000
1SNK516170R0000
1SNK522010R0000
1SNK522020R0000
1SNK522060R0000
1SNK522150R0000
1SNK526010R0000
1SNK526020R0000
1SNK526060R0000
1SNK526150R0000
1SNK531010R0000
1SNK531020R0000
1SNK531060R0000
1SNK536010R0000
1SNK536020R0000
1SNK536060R0000
1SNK705010R0000
1SNK705011R0000
1SNK705012R0000
1SNK705020R0000
1SNK705021R0000
1SNK705022R0000
1SNK705030R0000
1SNK705031R0000
1SNK705032R0000
1SNK705060R0000
1SNK705061R0000
1SNK705062R0000
1SNK705065R0000
1SNK705066R0000
1SNK705067R0000
1SNK705068R0000
1SNK705069R0000
1SNK705072R0000
1SNK705073R0000
1SNK705074R0000
1SNK705075R0000
1SNK705076R0000
1SNK705079R0000
1SNK705080R0000
1SNK705150R0000
1SNK705151R0000
1SNK705152R0000
1SNK705210R0000
1SNK705211R0000
1SNK705212R0000
1SNK705213R0000
1SNK705214R0000
1SNK705219R0000

ZS10-ST-1
ZS10-S
ZS10-SPZS10-S-BL
ZS4-SF1ZS4-SF1-T2
ZS4-SF1-R1
ZS4-SF1-R2
ZS4-SF1-R3
ZS4-SF1-R4
ZS4-S-R3
ZS10-S-R2
ZS10-SFZS4-S-R3-T2
ZS10-SF-R1
ZS10-SF-R3
ZS4-D2-SF1-R1
ZS4-D2-SF1-R3
ZS4-D2-SF1
ZS4-SF1-OR
ES10-ST
ES4-D2-SF1
ES4-SF
ZS16
ZS16-BL
ZS16-ORZS16-PE
ZS25
ZS25-BL
ZS25-YL
ZS25-PE
ZS35
ZS50
ZS35-BL
ZS50-BL
ZS35-ORZS50-YL
ZS50-RD
ZS50-BK
ZS35-PE
ZS50-PE
ZS35-PEN
ZS70
ZS70-BL
ZS70-YL
ZS70-PE
ZS95
ZS95-BL
ZS95-YL
ZS95-PE
ZS150
ZS150-BL
ZS150-YL
ZS240
ZS240-BL
ZS240-YL
ZK2.5
ZK2.5-3P
ZK2.5-4P
ZK2.5-BL
ZK2.5-3P-BL
ZK2.5-4P-BL
ZK2.5-OR
ZK2.5-3P-OR
ZK2.5-4P-OR
ZK2.5-YL
ZK2.5-GN
ZK2.5-RD
ZK2.5-WH
ZK2.5-BK
ZK2.5-3P-YL
ZK2.5-3P-GN
ZK2.5-3P-RD
ZK2.5-3P-WH
ZK2.5-3P-BK
ZK2.5-4P-YL
ZK2.5-4P-GN
ZK2.5-4P-RD
ZK2.5-4P-WH
ZK2.5-4P-BK
ZK2.5-PE
ZK2.5-PE-3P
ZK2.5-PE-4P
ZK2.5-D2
ZK2.5-D1
ZK2.5-D2-PE
ZK2.5-D-CH-UD
ZK2.5-D-CH-DU
ZK2.5-D-CH2-DU-RL

152
111
116
111
120
121
122
123
122
123
125
135
133
125
134
134
145
145
144
120
152
144
120
85
85
85
85
86
86
86
86
87
88
87
88
87
88
88
88
87
88
101
89
89
89
89
90
90
90
90
91
91
91
92
92
92
21
22
23
21
22
23
21
22
23
21
21
21
21
21
22
22
22
22
22
23
23
23
23
23
21
22
23
56
57
58
67
68
69

1SNK705220R0000
1SNK705250R0000
1SNK705310R0000
1SNK705311R0000
1SNK705312R0000
1SNK705313R0000
1SNK705320R0000
1SNK705321R0000
1SNK705330R0000
1SNK705331R0000
1SNK705510R0000
1SNK705511R0000
1SNK705512R0000
1SNK705513R0000
1SNK705550R0000
1SNK705710R0000
1SNK705711R0000
1SNK705910R0000
1SNK705911R0000
1SNK705912R0000
1SNK705913R0000
1SNK705960R0000
1SNK705961R0000
1SNK706010R0000
1SNK706011R0000
1SNK706012R0000
1SNK706020R0000
1SNK706021R0000
1SNK706022R0000
1SNK706030R0000
1SNK706031R0000
1SNK706032R0000
1SNK706060R0000
1SNK706062R0000
1SNK706066R0000
1SNK706150R0000
1SNK706151R0000
1SNK706152R0000
1SNK706310R0000
1SNK706410R0000
1SNK706411R0000
1SNK706412R0000
1SNK708010R0000
1SNK708011R0000
1SNK708020R0000
1SNK708021R0000
1SNK708030R0000
1SNK708031R0000
1SNK708060R0000
1SNK708062R0000
1SNK708066R0000
1SNK708150R0000
1SNK708151R0000
1SNK708911R0000
1SNK710010R0000
1SNK710011R0000
1SNK710020R0000
1SNK710021R0000
1SNK710030R0000
1SNK710063R0000
1SNK710064R0000
1SNK710065R0000
1SNK710067R0000
1SNK710150R0000
1SNK710151R0000
1SNK710910R0000
1SNK710911R0000
1SNK712010R0000
1SNK712011R0000
1SNK712020R0000
1SNK712021R0000
1SNK712063R0000
1SNK712064R0000
1SNK712065R0000
1SNK712067R0000
1SNK712150R0000
1SNK712151R0000
1SNK805010R0000
1SNK805013R0000
1SNK805014R0000
1SNK805015R0000
1SNK805016R0000
1SNK805017R0000
1SNK805020R0000
1SNK805025R0000
1SNK805150R0000
1SNK805152R0000
1SNK805156R0000
1SNK805212R0000

ZK2.5-D2-BL
ZK2.5-D1-PE
ZK2.5-S
ZK2.5-SP
ZK2.5-S-4P
ZK2.5-SP-4P
ZK2.5-S-BL
ZK2.5-S-4P-BL
ZK2.5-S-OR
ZK2.5-S-4P-OR
ZK2.5-T3
ZK2.5-T1
ZK2.5-L-L-PE
ZK2.5-L-N-PE
ZK2.5-T1-PE
ZK2.5-CH-4P-LR
ZK2.5-CH-4P-RL
EK2.5
EK2.5-3P
EK2.5-4P
EK2.5-S-4P
EK2.5-D2
EK2.5-T3
ZK4
ZK4-3P
ZK4-4P
ZK4-BLZK4-3P-BL
ZK4-4P-BL
ZK4-OR
ZK4-3P-OR
ZK4-4P-OR
ZK4-YLZK4-RDZK4-BK
ZK4-PEZK4-PE-3P
ZK4-PE-4P
ZK2.5-S-R1
ZK2.5-SF
ZK2.5-SF-R1
ZK2.5-SF-R3
ZK6
ZK6-3P
ZK6-BLZK6-3P-BL
ZK6-OR
ZK6-3P-OR
ZK6-YLZK6-RDZK6-BK
ZK6-PEZK6-PE-3P
EK6-3P
ZK10
ZK10-3P
ZK10-BL
ZK10-3P-BL
ZK10-OR
ZK10-PV
ZK10-3P-PV
ZK10-PV-BL
ZK10-3P-PV-BL
ZK10-PE
ZK10-PE-3P
EK10
EK10-3P
ZK16
ZK16-3P
ZK16-BLZK16-3P-BL
ZK16-PV
ZK16-3P-PV
ZK16-PV-BL
ZK16-3P-PV-BL
ZK16-PE
ZK16-PE-3P
ZDK2.5-22
ZDS4-22
ZDK2.5-21
ZDK2.5-11
ZD2.5-11
ZD2.5-22
ZDK2.5-22-BL
ZDK2.5-11-BL
ZDK2.5-11-PE
ZDK2.5-22-PE
ZD2.5-22-PE
ZDK2.5-D2-PE

56
56
49
52
50
53
49
50
49
50
60
61
62
63
60
65
66
21
22
23
50
56
60
24
25
26
24
25
26
24
25
26
24
24
24
24
25
26
51
51
55
55
27
28
27
28
27
28
27
27
27
27
28
28
29
31
29
31
29
30
32
30
32
30
32
29
31
33
35
33
35
34
36
34
36
34
36
177
190
176
175
172
173
177
175
179
180
174
183

1SNK805213R0000
1SNK805214R0000
1SNK805223R0000
1SNK805250R0000
1SNK805712R0000
1SNK805713R0000
1SNK805714R0000
1SNK805715R0000
1SNK805738R0000
1SNK805739R0000
1SNK805740R0000
1SNK805741R0000
1SNK805742R0000
1SNK805743R0000
1SNK805744R0000
1SNK805745R0000
1SNK805746R0000
1SNK805747R0000
1SNK805748R0000
1SNK805749R0000
1SNK805750R0000
1SNK805751R0000
1SNK805752R0000
1SNK805753R0000
1SNK805910R0000
1SNK805911R0000
1SNK805913R0000
1SNK805914R0000
1SNK805915R0000
1SNK805917R0000
1SNK806010R0000
1SNK806013R0000
1SNK806712R0000
1SNK806713R0000
1SNK806714R0000
1SNK900001R0000
1SNK900002R0000
1SNK900101R0000
1SNK900102R0000
1SNK900103R0000
1SNK900104R0000
1SNK900105R0000
1SNK900106R0000
1SNK900107R0000
1SNK900200R0000
1SNK900201R0000
1SNK900203R0000
1SNK900205R0000
1SNK900401R0000
1SNK900402R0000
1SNK900403R0000
1SNK900600R0000
1SNK900601R0000
1SNK900602R0000
1SNK900603R0000
1SNK900604R0000
1SNK900605R0000
1SNK900606R0000
1SNK900607R0000
1SNK900611R0000
1SNK900618R0000
1SNK900619R0000
1SNK900620R0000
1SNK900621R0000
1SNK900622R0000
1SNK900624R0000
1SNK900625R0000
1SNK900627R0000
1SNK900630R0000
1SNK900631R0000
1SNK900633R0000
1SNK900634R0000
1SNK900636R0000
1SNK900637R0000
1SNK900640R0000
1SNK900641R0000
1SNK900642R0000
1SNK900643R0000
1SNK900644R0000
1SNK900650R0000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNK900655R0000
1SNK900657R0000
1SNK900658R0000
1SNK900659R0000
1SNK900660R0000
1SNK905302R0000

ZDK2.5-D2
ZDK2.5-D1
ZDK2.5-D2-BL
ZDK2.5-D1-PE
CDK2.5
CDK2.5-E
CDS4
CDS4-E
CDK2.5-J
CDK2.5-J-E
CDK2.5-2P-J
CDK2.5-2P-J-E
CDK2.5-BL
CDK2.5-BL-E
CDK2.5-J-BL
CDK2.5-J-BL-E
CDK2.5-2P-J-BL
CDK2.5-2P-J-BL-E
CDK2.5-J-PE
CDK2.5-J-PE-E
CDK2.5-PE
CDK2.5-2P-J-PE
CDK2.5-2P-J-PE-E
CDK2.5-PE-E
EDK2.5-22
EDS4-22
EDK2.5-D
EDK2.5-21
EDK2.5-11
ED2.5-22
ZDK4-22
ZDS4-22-R1
CDK4
CDK4-E
CDS4-R1
BAM4
BAZ1
CS
BAZH1
CS-R1
ES-TC8
ES-TC6
CS-R2
CS-R3
TC5
TC5-R1TP2
TP4PG5
PG5-R1PG5-R2
SHBS
SHBP
SHB
JB85-3
CO
LH
LH-J
LH-R1
UMH
PL5
PL6
PL8
PL10
PL16
KCO
PT-3
RILS
MCLH
MCLH-R1
MCLH-YLMCLH-R1-YL
COP-ZD
VR-ZD
TO3.5-50
TO4-100
TO5.5-125
TO6.5-150
TO3.5-100-INS
PS-3
SC-JB8-2
SC-JB8-3
SC-JB8-4
SC-JB8-5
SC-JB8-3-OR
SC-JB8-4-OR
TO3.5-50-A
PT-ZD
JB5-2

181
182
181
184
172
172
190
190
186
186
187
187
175
175
186
186
187
187
186
186
174
187
187
174
177
190
181
176
172
173
178
192
178
178
192
80
30
80
56
80
27
24
21
30
21
21
30
30
52
52
211
80
21
56
21
155
199
56
199
30
80
81
84
85
87
155
210
219
201
201
201
201
172
185
213
213
213
213
213
213
152
156
156
231
231
231
213
185
21

PAGE 273

7

Index_1SNK160027C0206

Part Number

IndexPart Number classification
Part Number

Type

Page

1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK906302R0000
1SNK906303R0000
1SNK906304R0000
1SNK906305R0000
1SNK906310R0000
1SNK906350R0000
1SNK908302R0000
1SNK908303R0000
1SNK908304R0000
1SNK908305R0000
1SNK908310R0000
1SNK908902R0000
1SNK908903R0000
1SNK908904R0000
1SNK908905R0000
1SNK908910R0000
1SNK910302R0000
1SNK910303R0000
1SNK910304R0000
1SNK910305R0000
1SNK910310R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK916310R0000
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK922310R0000
1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK926310R0000

JB5-3
JB5-4
JB5-5
JB5-10JB5-50
JB6-2
JB6-3
JB6-4
JB6-5
JB6-10JB6-50
JB8-2
JB8-3
JB8-4
JB8-5
JB8-10
JB8-2-R1
JB8-3-R1
JB8-4-R1
JB8-5-R1
JB8-10-R1
JB10-2
JB10-3
JB10-4
JB10-5
JB10-10
JB12-2
JB12-3
JB12-5
JB16-2
JB16-3
JB16-4
JB16-5
JB16-10
JB22-2
JB22-3
JB22-5
JB22-10
JB26-2
JB26-3
JB26-5
JB26-10

21
21
21
21
21
24
24
24
24
24
24
27
27
27
27
27
154
154
154
154
154
29
29
29
29
29
30
30
30
87
87
87
87
87
89
89
89
89
90
90
90
90

Part Number

Type

Page

Part Number

Type

Page

Index_1SNK160027C0206

7

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

IndexType classification
Part Number

AJS9
1SNA179726R0200
AJS9-BK
1SNA206680R1500
1SNA206683R0400
AJS9-BLAJS9-BR
1SNA206782R0000
AJS9-GN
1SNA206681R0200
1SNA206682R0300
AJS9-GRAJS9-PR
1SNA206772R0000
AJS9-RD
1SNA206720R1400
1SNA206765R0000
AJS9-WH
1SNA206721R0100
AL4-M3
AMS 250 BASIC KIT
1SNA360000R2500
AMS 600 KIT
1SNA360000R2400
1SNA360155R1700
AMS CLEANER FLUIDAMS CLEANER KIT
1SNA360156R1000AMS INK CARTRIDGES
1SNA360150R2600
AMS PEN 0.18
1SNA360103R1400
AMS PEN 0.25
1SNA360100R2500
AMS PEN 0.35
1SNA360101R1200
AMS PEN 0.50
1SNA360104R1500
AMS PEN 0.70
1SNA360105R1600
AMS PEN 1.00
1SNA360106R1700
ANT
1SNA168675R1400
BAM4
1SNK900001R0000
BAZ1
1SNK900002R0000
BAZH1
1SNK900102R0000
BJMI31.2
1SNA206053R0700
BJMI31.3
1SNA206054R0000
BJMI36.2
1SNA206126R2500
BJMI36.3
1SNA206223R0600
CDK2.5
1SNK805712R0000
CDK2.5-2P-J
1SNK805740R0000
CDK2.5-2P-J-BL
1SNK805746R0000
1SNK805747R0000
CDK2.5-2P-J-BL-E
CDK2.5-2P-J-E
1SNK805741R0000
CDK2.5-2P-J-PE
1SNK805751R0000
CDK2.5-2P-J-PE-E
1SNK805752R0000
CDK2.5-BL
1SNK805742R0000
1SNK805743R0000
CDK2.5-BL-E
CDK2.5-E
1SNK805713R0000
CDK2.5-J
1SNK805738R0000
CDK2.5-J-BL
1SNK805744R0000
CDK2.5-J-BL-E
1SNK805745R0000
1SNK805739R0000
CDK2.5-J-E
CDK2.5-J-PE
1SNK805748R0000
CDK2.5-J-PE-E
1SNK805749R0000
CDK2.5-PE
1SNK805750R0000
CDK2.5-PE-E
1SNK805753R0000
1SNK806712R0000
CDK4
CDK4-E
1SNK806713R0000
CDS4
1SNK805714R0000
CDS4-E
1SNK805715R0000
CDS4-R1
1SNK806714R0000
1SNA179371R1600
CN5CO
1SNK900604R0000
COP-ZD
1SNK900636R0000
CPBP1
1SNA399788R1600CPBP2
1SNA399787R0500
1SNK900101R0000
CS
CS-R1
1SNK900103R0000
CS-R2
1SNK900106R0000
CS-R3
1SNK900107R0000
DISPOSABLE AMS PEN 0.25
1SNAt360120R1000DISPOSABLE AMS PEN 0.35
1SNA360121R0500
DISPOSABLE AMS PEN ED-R 0.18 1SNA360124R1000DISPOSABLE AMS PEN ED-R 0.25 1SNA360122R1000DISPOSABLE AMS PEN ED-R 0.35 1SNA360123R0500
DUST COVER
1SNA360161R1500
ED2.5-22
1SNK805917R0000
EDK2.5-11
1SNK805915R0000
EDK2.5-21
1SNK805914R0000
EDK2.5-22
1SNK805910R0000
EDK2.5-D
1SNK805913R0000
EDS4-22
1SNK805911R0000
EK10
1SNK710910R0000
EK10-3P
1SNK710911R0000
EK2.5
1SNK705910R0000
EK2.5-3P
1SNK705911R0000
EK2.5-4P
1SNK705912R0000
EK2.5-D2
1SNK705960R0000
EK2.5-S-4P
1SNK705913R0000
EK2.5-T3
1SNK705961R0000
EK6-3P
1SNK708911R0000
EPR1
1SNA178431R2200
1SNA399726R0700
EPR2
ES10-ST
1SNK508910R0000
ES4
1SNK505910R0000
ES4-D2
1SNK505960R0000
ES4-D2-SF1
1SNK508911R0000
1SNK508960R0000
ES4-SF

Page

TypePart Number

Page

152
154
154
154
154
154
154
154
154
152
267
245
268
268
268
268
268
268
268
268
268
120
80
30
56
91
91
92
92
172
187
187
187
187
187
187
175
175
172
186
186
186
186
186
186
174
174
178
178
190
190
192
120
155
172
91
92
80
80
21
30
268
268
268
268
268
265
173
172
176
177
181
190
29
31
21
22
23
56
50
60
28
201
201
152
80
136
144
120

ES4-T3
ES6-3S
ES6-4S
ES-TC6
ES-TC8
HTP500-BAS
HTP500-CLEAN
HTP500-FEED
HTP500-PL
HTP500-PL2
HTP500-PRINT
HTP500-PW
HTP500-ROLL
HTP500-WB
HTS500
JB10-10
JB10-2
JB10-3
JB10-4
JB10-5
JB12-2
JB12-3
JB12-5
JB16-10
JB16-2
JB16-3
JB16-4
JB16-5
JB22-10
JB22-2
JB22-3
JB22-5
JB26-10
JB26-2
JB26-3
JB26-5JB5-10
JB5-2
JB5-3
JB5-4
JB5-5
JB5-50
JB6-10
JB6-2
JB6-3
JB6-4
JB6-5
JB6-50
JB8-10
JB8-10-R1
JB8-2
JB8-2-R1
JB8-3
JB8-3-R1
JB8-4
JB8-4-R1
JB8-5
JB85-3
JB8-5-R1
KCO
LH
LH-J
LH-R1
MC512
MC512PA

1SNK505961R0000
1SNK505912R0000
1SNK505911R0000
1SNK900105R0000
1SNK900104R0000
1SNA235706R0700
1SNA235714R2600
1SNA235703R0400
1SNA235704R0500
1SNA235705R0600
1SNA235716R2000
1SNA235709R1200
1SNA235715R2700
1SNA235717R2100
1SNA235702R0300
1SNK910310R0000
1SNK910302R0000
1SNK910303R0000
1SNK910304R0000
1SNK910305R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK916310R0000
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK922310R0000
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK926310R0000
1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK905310R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905350R0000
1SNK906310R0000
1SNK906302R0000
1SNK906303R0000
1SNK906304R0000
1SNK906305R0000
1SNK906350R0000
1SNK908310R0000
1SNK908910R0000
1SNK908302R0000
1SNK908902R0000
1SNK908303R0000
1SNK908903R0000
1SNK908304R0000
1SNK908904R0000
1SNK908305R0000
1SNK900603R0000
1SNK908905R0000
1SNK900624R0000
1SNK900605R0000
1SNK900606R0000
1SNK900607R0000
1SNK140000R0000
1SNK140011R0000
1SNK140012R0000
1SNK140021R0000
1SNK140022R0000
1SNK140031R0000
1SNK140032R0000
1SNK140041R0000
1SNK140042R0000
1SNK140051R0000
1SNK140052R0000
1SNK140061R0000
1SNK140062R0000
1SNK140071R0000
1SNK140072R0000
1SNK140081R0000
1SNK140082R0000
1SNK140083R0000
1SNK140084R0000
1SNK140091R0000
1SNK140092R0000
1SNK140101R0000
1SNK140102R0000
1SNK140111R0000
1SNK140112R0000
1SNK140121R0000

146
82
83
24
27
265
265
265
265
265
265
265
265
265
265
29
29
29
29
29
30
30
30
87
87
87
87
87
89
89
89
89
90
90
90
90
21
21
21
21
21
21
24
24
24
24
24
24
27
154
27
154
27
154
27
154
27
21
154
155
199
56
199
21
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246

Type

Part Number

Page

1SNK140122R0000
1SNK140131R0000
1SNK140132R0000
1SNK140141R0000
1SNK140142R0000
1SNK140151R0000
1SNK140152R0000
1SNK140161R0000
1SNK140162R0000
1SNK140171R0000
1SNK140172R0000
1SNK140181R0000
1SNK140182R0000
1SNK140191R0000
1SNK140192R0000
1SNK140201R0000
1SNK140202R0000
1SNK145011R0000
1SNK145012R0000
1SNK145021R0000
1SNK145022R0000
1SNK145031R0000
1SNK145032R0000
1SNK145041R0000
1SNK145042R0000
1SNK145051R0000
1SNK145052R0000
1SNK145061R0000
1SNK145062R0000
1SNK145071R0000
1SNK145072R0000
1SNK145081R0000
1SNK145082R0000
1SNK145091R0000
1SNK145092R0000
1SNK145102R0000
1SNK146011R0000
1SNK146012R0000
1SNK146021R0000
1SNK146022R0000
1SNK146031R0000
1SNK146032R0000
1SNK146041R0000
1SNK146042R0000
1SNK146051R0000
1SNK146052R0000
1SNK146061R0000
1SNK146062R0000
1SNK146071R0000
1SNK146072R0000
1SNK146081R0000
1SNK146082R0000
1SNK146091R0000
1SNK146092R0000
1SNK146101R0000
1SNK146102R0000
1SNK146111R0000
1SNK146112R0000
1SNK146121R0000
1SNK146122R0000
1SNK146131R0000
1SNK146132R0000
1SNK146141R0000
1SNK146142R0000
1SNK146151R0000
1SNK146152R0000
1SNK146161R0000
1SNK146162R0000
1SNK146171R0000
1SNK146172R0000
1SNK146181R0000
1SNK146182R0000
1SNK146191R0000
1SNK146192R0000
1SNK146201R0000
1SNK146202R0000
1SNK146211R0000
1SNK146212R0000
1SNK146221R0000
1SNK146222R0000
1SNK146231R0000
1SNK146232R0000
1SNK146241R0000
1SNK146242R0000
1SNK146251R0000
1SNK146252R0000
1SNK146261R0000
1SNK146262R0000
1SNK147001R0000

248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
248
246
249
246
249
246
249
247
249
247

PAGE 275

7

Index_1SNK160027C0206

Type

Type

7

MC512-YL
MC612
MC612PAPart Number

Page

1SNK147002R0000
1SNK147011R0000
1SNK147012R0000
1SNK147021R0000
1SNK147022R0000
1SNK147031R0000
1SNK147032R0000
1SNK147041R0000
1SNK147042R0000
1SNK147051R0000
1SNK147052R0000
1SNK147061R0000
1SNK147062R0000
1SNK147071R0000
1SNK147072R0000
1SNK147081R0000
1SNK147082R0000
1SNK147091R0000
1SNK147092R0000
1SNK148001R0000
1SNK148002R0000
1SNK148011R0000
1SNK148012R0000
1SNK148021R0000
1SNK148022R0000
1SNK148031R0000
1SNK148032R0000
1SNK148041R0000
1SNK148042R0000
1SNK148051R0000
1SNK148052R0000
1SNK148061R0000
1SNK148062R0000
1SNK148071R0000
1SNK148072R0000
1SNK148091R0000
1SNK148092R0000
1SNK148101R0000
1SNK148102R0000
1SNK148111R0000
1SNK148112R0000
1SNK148121R0000
1SNK148122R0000
1SNK148131R0000
1SNK148132R0000
1SNK148141R0000
1SNK148142R0000
1SNK148151R0000
1SNK148152R0000
1SNK148161R0000
1SNK148162R0000
1SNK148171R0000
1SNK148172R0000
1SNK148181R0000
1SNK148182R0000
1SNK148192R0000
1SNK148202R0000
1SNK148212R0000
1SNK148222R0000
1SNK149001R0000
1SNK149002R0000
1SNK149011R0000
1SNK149012R0000
1SNK149999R0000
1SNK140004R0000
1SNK150000R0000
1SNK150011R0000
1SNK150012R0000
1SNK150021R0000
1SNK150022R0000
1SNK150031R0000
1SNK150032R0000
1SNK150041R0000
1SNK150042R0000
1SNK150051R0000
1SNK150052R0000
1SNK150061R0000
1SNK150062R0000
1SNK150071R0000
1SNK150072R0000
1SNK150081R0000
1SNK150082R0000
1SNK150083R0000
1SNK150084R0000
1SNK150091R0000
1SNK150092R0000
1SNK150101R0000
1SNK150102R0000
1SNK150111R0000

249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
247
249
249
249
249
249
247
249
247
249
21
244
24
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252

Type

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPart Number

Page

1SNK150112R0000
1SNK150121R0000
1SNK150122R0000
1SNK150131R0000
1SNK150132R0000
1SNK150141R0000
1SNK150142R0000
1SNK150151R0000
1SNK150152R0000
1SNK150161R0000
1SNK150162R0000
1SNK150171R0000
1SNK150172R0000
1SNK150181R0000
1SNK150182R0000
1SNK150191R0000
1SNK150192R0000
1SNK150201R0000
1SNK150202R0000
1SNK155011R0000
1SNK155012R0000
1SNK155021R0000
1SNK155022R0000
1SNK155031R0000
1SNK155032R0000
1SNK155041R0000
1SNK155042R0000
1SNK155051R0000
1SNK155052R0000
1SNK155061R0000
1SNK155062R0000
1SNK155071R0000
1SNK155072R0000
1SNK155081R0000
1SNK155082R0000
1SNK155091R0000
1SNK155092R0000
1SNK155102R0000
1SNK156011R0000
1SNK156012R0000
1SNK156021R0000
1SNK156022R0000
1SNK156031R0000
1SNK156032R0000
1SNK156041R0000
1SNK156042R0000
1SNK156051R0000
1SNK156052R0000
1SNK156061R0000
1SNK156062R0000
1SNK156071R0000
1SNK156072R0000
1SNK156081R0000
1SNK156082R0000
1SNK156091R0000
1SNK156092R0000
1SNK156101R0000
1SNK156102R0000
1SNK156111R0000
1SNK156112R0000
1SNK156121R0000
1SNK156122R0000
1SNK156131R0000
1SNK156132R0000
1SNK156141R0000
1SNK156142R0000
1SNK156151R0000
1SNK156152R0000
1SNK156161R0000
1SNK156162R0000
1SNK156171R0000
1SNK156172R0000
1SNK156181R0000
1SNK156182R0000
1SNK156191R0000
1SNK156192R0000
1SNK156201R0000
1SNK156202R0000
1SNK156211R0000
1SNK156212R0000
1SNK156221R0000
1SNK156222R0000
1SNK156231R0000
1SNK156232R0000
1SNK156241R0000
1SNK156242R0000
1SNK156251R0000
1SNK156252R0000
1SNK156261R0000

254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
252
254
253
254
253
255
253

Type

MC612-YL
MC812
MC812PAPart Number

Page

1SNK156262R0000
1SNK157001R0000
1SNK157002R0000
1SNK157011R0000
1SNK157012R0000
1SNK157021R0000
1SNK157022R0000
1SNK157031R0000
1SNK157032R0000
1SNK157041R0000
1SNK157042R0000
1SNK157051R0000
1SNK157052R0000
1SNK157061R0000
1SNK157062R0000
1SNK157071R0000
1SNK157072R0000
1SNK157081R0000
1SNK157082R0000
1SNK157091R0000
1SNK157092R0000
1SNK158001R0000
1SNK158002R0000
1SNK158011R0000
1SNK158012R0000
1SNK158021R0000
1SNK158022R0000
1SNK158031R0000
1SNK158032R0000
1SNK158041R0000
1SNK158042R0000
1SNK158051R0000
1SNK158052R0000
1SNK158061R0000
1SNK158062R0000
1SNK158071R0000
1SNK158072R0000
1SNK158091R0000
1SNK158092R0000
1SNK158101R0000
1SNK158102R0000
1SNK158111R0000
1SNK158112R0000
1SNK158121R0000
1SNK158122R0000
1SNK158131R0000
1SNK158132R0000
1SNK158141R0000
1SNK158142R0000
1SNK158151R0000
1SNK158152R0000
1SNK158161R0000
1SNK158162R0000
1SNK158171R0000
1SNK158172R0000
1SNK158181R0000
1SNK158182R0000
1SNK158192R0000
1SNK158202R0000
1SNK158212R0000
1SNK158222R0000
1SNK159001R0000
1SNK159002R0000
1SNK159011R0000
1SNK159012R0000
1SNK159999R0000
1SNK150004R0000
1SNK160000R0000
1SNK160011R0000
1SNK160012R0000
1SNK160021R0000
1SNK160022R0000
1SNK160031R0000
1SNK160032R0000
1SNK160041R0000
1SNK160042R0000
1SNK160051R0000
1SNK160052R0000
1SNK160061R0000
1SNK160062R0000
1SNK160071R0000
1SNK160072R0000
1SNK160081R0000
1SNK160082R0000
1SNK160083R0000
1SNK160084R0000
1SNK160091R0000
1SNK160092R0000
1SNK160101R0000

255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
253
255
255
255
255
255
253
255
253
255
24
250
30
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257

Index_1SNK160027C0206

Index
Type classification

IndexType classification
Part Number

Page

1SNK160102R0000
1SNK160111R0000
1SNK160112R0000
1SNK160121R0000
1SNK160122R0000
1SNK160131R0000
1SNK160132R0000
1SNK160141R0000
1SNK160142R0000
1SNK160151R0000
1SNK160152R0000
1SNK160161R0000
1SNK160162R0000
1SNK160171R0000
1SNK160172R0000
1SNK160181R0000
1SNK160182R0000
1SNK160191R0000
1SNK160192R0000
1SNK160201R0000
1SNK160202R0000
1SNK165011R0000
1SNK165012R0000
1SNK165021R0000
1SNK165022R0000
1SNK165031R0000
1SNK165032R0000
1SNK165041R0000
1SNK165042R0000
1SNK165051R0000
1SNK165052R0000
1SNK165061R0000
1SNK165062R0000
1SNK165071R0000
1SNK165072R0000
1SNK165081R0000
1SNK165082R0000
1SNK165091R0000
1SNK165092R0000
1SNK165102R0000
1SNK166011R0000
1SNK166012R0000
1SNK166021R0000
1SNK166022R0000
1SNK166031R0000
1SNK166032R0000
1SNK166041R0000
1SNK166042R0000
1SNK166051R0000
1SNK166052R0000
1SNK166061R0000
1SNK166062R0000
1SNK166071R0000
1SNK166072R0000
1SNK166081R0000
1SNK166082R0000
1SNK166091R0000
1SNK166092R0000
1SNK166101R0000
1SNK166102R0000
1SNK166111R0000
1SNK166112R0000
1SNK166121R0000
1SNK166122R0000
1SNK166131R0000
1SNK166132R0000
1SNK166141R0000
1SNK166142R0000
1SNK166151R0000
1SNK166152R0000
1SNK166161R0000
1SNK166162R0000
1SNK166171R0000
1SNK166172R0000
1SNK166181R0000
1SNK166182R0000
1SNK166191R0000
1SNK166192R0000
1SNK166201R0000
1SNK166202R0000
1SNK166211R0000
1SNK166212R0000
1SNK166221R0000
1SNK166222R0000
1SNK166231R0000
1SNK166232R0000
1SNK166241R0000
1SNK166242R0000
1SNK166251R0000

259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
257
259
258
260
258
260
258

Type

Part Number

Page

Type

Part Number

Page

MC812-YL
MCLH
MCLH-R1
MCLH-R1-YL
MCLH-YL
MG2-ABM 991012
MG2-CKP 991670
MG2-CTB 991006
MG2-ETB 991016
MG2-ETR 991600
MG2-ETR 991601
MG2-ETR 991602
MG2-ETR 991603
MG2-ETR 991606
MG2-LTB 991013
MG2-MTB 991008
MG2-PLT 991002
MG2-PTD 991007
MG2-PTM 991010
MG2-PWC 991000
MG2-QTB 991011

1SNK166252R0000
1SNK166261R0000
1SNK166262R0000
1SNK167001R0000
1SNK167002R0000
1SNK167011R0000
1SNK167012R0000
1SNK167021R0000
1SNK167022R0000
1SNK167031R0000
1SNK167032R0000
1SNK167041R0000
1SNK167042R0000
1SNK167051R0000
1SNK167052R0000
1SNK167061R0000
1SNK167062R0000
1SNK167071R0000
1SNK167072R0000
1SNK167081R0000
1SNK167082R0000
1SNK167091R0000
1SNK167092R0000
1SNK168001R0000
1SNK168002R0000
1SNK168011R0000
1SNK168012R0000
1SNK168021R0000
1SNK168022R0000
1SNK168031R0000
1SNK168032R0000
1SNK168041R0000
1SNK168042R0000
1SNK168051R0000
1SNK168052R0000
1SNK168061R0000
1SNK168062R0000
1SNK168071R0000
1SNK168072R0000
1SNK168091R0000
1SNK168092R0000
1SNK168101R0000
1SNK168102R0000
1SNK168111R0000
1SNK168112R0000
1SNK168121R0000
1SNK168122R0000
1SNK168131R0000
1SNK168132R0000
1SNK168141R0000
1SNK168142R0000
1SNK168151R0000
1SNK168152R0000
1SNK168161R0000
1SNK168162R0000
1SNK168171R0000
1SNK168172R0000
1SNK168181R0000
1SNK168182R0000
1SNK168192R0000
1SNK168202R0000
1SNK168212R0000
1SNK168222R0000
1SNK169001R0000
1SNK169002R0000
1SNK169011R0000
1SNK169012R0000
1SNK169999R0000
1SNK160004R0000
1SNK900630R0000
1SNK900631R0000
1SNK900634R0000
1SNK900633R0000
1SNB991012R0000
1SNB991670R0000
1SNB991006R0000
1SNB991016R0000
1SNB991600R0000
1SNB991601R0000
1SNB991602R0000
1SNB991603R0000
1SNB991606R0000
1SNB991013R0000
1SNB991008R0000
1SNB991002R0000
1SNB991007R0000
1SNB991010R0000
1SNB991000R0000
1SNB991011R0000

260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
258
260
260
260
260
260
258
260
258
260
30
256
201
201
201
201
266
266
266
244
266
266
266
266
266
266
266
266
266
261
266
266

MG2-STB 991005
MG2-TCT 991562
MG2-TDMO-01 40340
MG2-TDMO-01 40341
MG2-TDMO-01 40390
MG2-TDMO-01 40391
MG2-TDMO-02 40440
MG2-TDMO-02 40441
MG2-TDMO-02 40490
MG2-TDMO-02 40491
MG2-TDMO-03 40540
MG2-TDMO-03 40541
MG2-TDMO-03 40590
MG2-TDMO-03 40591
MG2-TGT 991532
MG2-TLT 991522
MG2-TMT 991513
MG2-TST 991552
MG2-TTB 991512
MG2-TTD 991563
MG2-TWC 991502
MG2-TWT 991542
MG2-WTB 991004
MG3 KIT
MG-CPM 13 41740
MG-CPM 13 41741
MG-CPM 13 41790
MG-CPM 13 41791
MG-CPMFA 43196
MG-TAA 49148
MG-TAA 49198
MG-TAA 49448
MG-TAA 49498
MG-TAPW 49046
MG-TAPW 49096
MG-TAR 45194
MG-TAR 45490
MG-VYT 46415
MG-VYT 46915
PAM43020
PC5-10
PC5-2
PC8-10PC81-10
PC8-2
PC8-3
PC8-4
PC8-R1
PC8-R2
PC8-R3
PC8-R4
PC8-R5
PC8-R6
PC8-R7PC8-R8PEN HOLDER
PG5
PG5-R1PG5-R2
PIB2-TT
PIB2-TT-YL
PL10
PL16
PL5
PL6
PL8
PR3.G2PR3.Z2
PR30
PR4
PR5
PR50
PS-3
PT-3
PT-ZD
RC1010RCPEAD-TT
RCPEAD-TT-YL
RCPEB
RIB-B
RIB-R
RIB-RSRILS
SC-JB8-2
SC-JB8-3
SC-JB8-3-OR
SC-JB8-4
SC-JB8-4-OR
SC-JB8-5

1SNB991005R0000
1SNB991562R0000
1SNB040340R0412
1SNB040341R0416
1SNB040390R0412
1SNB040391R0416
1SNB040440R0412
1SNB040441R0416
1SNB040490R0412
1SNB040491R0416
1SNB040540R0412
1SNB040541R0416
1SNB040590R0412
1SNB040591R0416
1SNB991532R0000
1SNB991522R0000
1SNB991513R0000
1SNB991552R0000
1SNB991512R0000
1SNB991563R0000
1SNB991502R0000
1SNB991542R0000
1SNB991004R0000
1SNB419001R0000
1SNB041740R0512
1SNB041741R0612
1SNB041790R0512
1SNB041791R0612
1SNB043196R0012
1SNB049148R1735
1SNB049198R1735
1SNB049448R8530
1SNB049498R8530
1SNB049046R0929
1SNB049096R0929
1SNB045194R1735
1SNB045490R8530
1SNB046415R0615
1SNB046915R0615
1SNA235106R2600
1SNA113544R1200
1SNA113542R1000
1SNA163313R2400
1SNA173523R1100
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400842R0000
1SNA400843R0000
1SNA400849R0000
1SNA400850R0000
1SNA360098R1200
1SNK900401R0000
1SNK900402R0000
1SNK900403R0000
1SNA235155R2600
1SNA235157R2000
1SNK900621R0000
1SNK900622R0000
1SNK900618R0000
1SNK900619R0000
1SNK900620R0000
1SNA164800R0300
1SNA174300R1700
1SNA173220R0500
1SNA168500R1200
1SNA168700R2200
1SNA178529R0400
1SNK900650R0000
1SNK900625R0000
1SNK900660R0000
1SNA238000R1600
1SNA235158R0100
1SNA235159R0200
1SNA178430R0500
1SNA235710R0600
1SNA235711R2300
1SNA235718R0200
1SNK900627R0000
1SNK900652R0000
1SNK900653R0000
1SNK900657R0000
1SNK900654R0000
1SNK900658R0000
1SNK900655R0000

266
266
261
261
261
261
261
261
261
261
261
261
261
261
266
266
266
266
266
266
266
266
266
244
244
250
21
30
185
201
201
201
201
263
263
201
201
217
217
230
105
105
155
120
226
226
226
153
155
155
155
155
155
155
155
268
52
52
211
201
201
85
87
80
81
84
197
196
196
198
198
197
213
210
185
91
201
201
201
265
265
265
219
152
156
231
156
231
231

PAGE 277

7

Index_1SNK160027C0206

TypeIndexType classification
Part Number

Page

Type

Part Number

Page

Type

SERVICE KIT FOR AMS 500
SHB
SHBP
SHBS
SPDST1SPRC 1SPRC 10SPRC 11SPRC 13SPRC 14SPRC 15SPRC 16SPRC 2SPRC 21SPRC 26
SPRC 27
SPRC 28
SPRC 29
SPRC 30-3
SPRC 4SPRC 5SPRC 6SPRC 7SPRC 8SPRC 9TC5
TC5-R1TGA8

1SNA360162R1600
1SNK900602R0000
1SNK900601R0000
1SNK900600R0000
1SNA360163R1700
1SNA360010R1500
1SNA360020R1700
1SNA360021R0400
1SNA360023R0600
1SNA360024R0700
1SNA360025R0000
1SNA360026R0100
1SNA360011R1500
1SNA360031R0600
1SNA360036R0300
1SNA360037R0400
1SNA360040R2300
1SNA360038R1500
1SNA360039R1700
1SNA360014R0500
1SNA360015R0600
1SNA360016R0700
1SNA360017R0000
1SNA360018R1100
1SNA360019R1200
1SNK900200R0000
1SNK900201R0000
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNK900644R0000
1SNK900640R0000
1SNK900659R0000
1SNK900641R0000
1SNK900642R0000
1SNK900643R0000
1SNK900203R0000
1SNK900205R0000
1SNK900611R0000
1SNK900637R0000
1SNK805016R0000
1SNK805017R0000
1SNK805156R0000
1SNK805015R0000
1SNK805025R0000
1SNK805150R0000
1SNK805014R0000
1SNK805010R0000
1SNK805020R0000
1SNK805152R0000
1SNK805214R0000
1SNK805250R0000
1SNK805213R0000
1SNK805223R0000
1SNK805212R0000
1SNK806010R0000
1SNK805013R0000
1SNK806013R0000
1SNK710010R0000
1SNK710011R0000
1SNK710021R0000
1SNK710064R0000
1SNK710067R0000
1SNK710020R0000
1SNK710030R0000
1SNK710150R0000
1SNK710151R0000
1SNK710063R0000
1SNK710065R0000
1SNK712010R0000
1SNK712011R0000
1SNK712021R0000
1SNK712064R0000
1SNK712067R0000
1SNK712020R0000
1SNK712150R0000
1SNK712151R0000
1SNK712063R0000
1SNK712065R0000
1SNK705010R0000
1SNK705011R0000
1SNK705073R0000
1SNK705021R0000
1SNK705068R0000
1SNK705031R0000
1SNK705069R0000
1SNK705072R0000
1SNK705067R0000
1SNK705012R0000

268
56
21
80
268
268
268
268
268
268
268
268
268
264
268
268
268
268
245
268
268
268
268
268
268
21
21
120
120
120
213
213
213
213
213
213
30
30
30
185
172
173
174
175
175
179
176
177
177
180
182
184
181
181
183
178
190
192
29
31
31
32
32
29
29
30
32
30
30
33
35
35
36
36
33
34
36
34
34
21
22
22
22
22
22
22
22
22
23

ZK2.5-4P-BK
ZK2.5-4P-BL
ZK2.5-4P-GN
ZK2.5-4P-OR
ZK2.5-4P-RD
ZK2.5-4P-WH
ZK2.5-4P-YL
ZK2.5-BK
ZK2.5-BL
ZK2.5-CH-4P-LR
ZK2.5-CH-4P-RL
ZK2.5-D1
ZK2.5-D1-PE
ZK2.5-D2
ZK2.5-D2-BL
ZK2.5-D2-PE
ZK2.5-D-CH2-DU-RL
ZK2.5-D-CH-DU
ZK2.5-D-CH-UD
ZK2.5-GN
ZK2.5-L-L-PE
ZK2.5-L-N-PE
ZK2.5-OR
ZK2.5-PE
ZK2.5-PE-3P
ZK2.5-PE-4P
ZK2.5-RD
ZK2.5-S
ZK2.5-S-4P
ZK2.5-S-4P-BL
ZK2.5-S-4P-OR
ZK2.5-S-BL
ZK2.5-SF
ZK2.5-SF-R1
ZK2.5-SF-R3
ZK2.5-S-OR
ZK2.5-SP
ZK2.5-SP-4P
ZK2.5-S-R1
ZK2.5-T1
ZK2.5-T1-PE
ZK2.5-T3
ZK2.5-WH
ZK2.5-YL
ZK4
ZK4-3P
ZK4-3P-BL
ZK4-3P-OR
ZK4-4P
ZK4-4P-BL
ZK4-4P-OR
ZK4-BK
ZK4-BLZK4-ORZK4-PEZK4-PE-3P
ZK4-PE-4P
ZK4-RDZK4-YL
ZK6
ZK6-3P
ZK6-3P-BL
ZK6-3P-OR
ZK6-BKZK6-BLZK6-ORZK6-PEZK6-PE-3P
ZK6-RDZK6-YLZS10
ZS10-BK
ZS10-BL
ZS10-BR
ZS10-GN
ZS10-ORZS10-PE
ZS10-PE-R1
ZS10-PR
ZS10-R1
ZS10-RD
ZS10-S
ZS10-S-BL
ZS10-SF
ZS10-SF-R1
ZS10-SF-R3
ZS10-SPZS10-S-R2
ZS10-ST

1SNK705080R0000
1SNK705022R0000
1SNK705075R0000
1SNK705032R0000
1SNK705076R0000
1SNK705079R0000
1SNK705074R0000
1SNK705066R0000
1SNK705020R0000
1SNK705710R0000
1SNK705711R0000
1SNK705211R0000
1SNK705250R0000
1SNK705210R0000
1SNK705220R0000
1SNK705212R0000
1SNK705219R0000
1SNK705214R0000
1SNK705213R0000
1SNK705061R0000
1SNK705512R0000
1SNK705513R0000
1SNK705030R0000
1SNK705150R0000
1SNK705151R0000
1SNK705152R0000
1SNK705062R0000
1SNK705310R0000
1SNK705312R0000
1SNK705321R0000
1SNK705331R0000
1SNK705320R0000
1SNK706410R0000
1SNK706411R0000
1SNK706412R0000
1SNK705330R0000
1SNK705311R0000
1SNK705313R0000
1SNK706310R0000
1SNK705511R0000
1SNK705550R0000
1SNK705510R0000
1SNK705065R0000
1SNK705060R0000
1SNK706010R0000
1SNK706011R0000
1SNK706021R0000
1SNK706031R0000
1SNK706012R0000
1SNK706022R0000
1SNK706032R0000
1SNK706066R0000
1SNK706020R0000
1SNK706030R0000
1SNK706150R0000
1SNK706151R0000
1SNK706152R0000
1SNK706062R0000
1SNK706060R0000
1SNK708010R0000
1SNK708011R0000
1SNK708021R0000
1SNK708031R0000
1SNK708066R0000
1SNK708020R0000
1SNK708030R0000
1SNK708150R0000
1SNK708151R0000
1SNK708062R0000
1SNK708060R0000
1SNK508010R0000
1SNK508066R0000
1SNK508020R0000
1SNK508064R0000
1SNK508061R0000
1SNK508030R0000
1SNK508150R0000
1SNK508151R0000
1SNK508063R0000
1SNK508011R0000
1SNK508062R0000
1SNK508315R0000
1SNK508320R0000
1SNK508418R0000
1SNK508421R0000
1SNK508422R0000
1SNK508316R0000
1SNK508417R0000
1SNK508310R0000

23
23
23
23
23
23
23
21
21
65
66
57
56
56
56
58
69
68
67
21
62
63
21
21
22
23
21
49
50
50
50
49
51
55
55
49
52
53
51
61
60
60
21
21
24
25
25
25
26
26
26
24
24
24
24
25
26
24
24
27
28
28
28
27
27
27
27
28
27
27
84
84
84
84
84
84
84
153
84
152
84
111
111
133
134
134
116
135
154

ZS10-ST-1
ZS10-ST-T4
ZS10-WH
ZS10-YL
ZS150
ZS150-BL
ZS150-YL
ZS16
ZS16-BL
ZS16-ORZS16-PE
ZS240
ZS240-BL
ZS240-YL
ZS25
ZS25-BL
ZS25-PE
ZS25-YL
ZS35
ZS35-BL
ZS35-ORZS35-PE
ZS35-PEN
ZS4ZS4-BK
ZS4-BLZS4-BRZS4-D1ZS4-D2ZS4-D2-BL
ZS4-D2-OR
ZS4-D2-S
ZS4-D2-SF1
ZS4-D2-SF1-R1
ZS4-D2-SF1-R3
ZS4-D2-S-T2
ZS4-D-CH-DU
ZS4-D-CH-UD
ZS4-GNZS4-ORZS4-PEZS4-PE-R2
ZS4-PRZS4-R1ZS4-R2ZS4-RDZS4-S
ZS4-S-BLZS4-SFZS4-SF1ZS4-SF1-OR
ZS4-SF1-R1
ZS4-SF1-R2
ZS4-SF1-R3
ZS4-SF1-R4
ZS4-SF1-T2
ZS4-SF-R1
ZS4-SF-R2
ZS4-SF-R3
ZS4-SF-R4ZS4-SF-T2
ZS4-S-ORZS4-SPZS4-SP-R1
ZS4-SP-T2
ZS4-SP-T2-R1
ZS4-S-R1
ZS4-S-R1-BL
ZS4-S-R1-OR
ZS4-S-R2ZS4-S-R3ZS4-S-R3-T2
ZS4-S-T2ZS4-S-T2.3
ZS4-S-T2.3-R1
ZS4-S-T2-BL
ZS4-S-T2-OR
ZS4-S-T2-R1
ZS4-S-T2-R1-BL
ZS4-S-T2-R1-OR
ZS4-T3ZS4-T3-R1
ZS4-WHZS4-YL
ZS50
ZS50-BK
ZS50-BL
ZS50-PE
ZS50-RD

TO3.5-100-INS
TO3.5-50
TO3.5-50-A
TO4-100
TO5.5-125
TO6.5-150
TP2
TP4
UMH
VR-ZD
ZD2.5-11
ZD2.5-22
ZD2.5-22-PE
ZDK2.5-11
ZDK2.5-11-BL
ZDK2.5-11-PE
ZDK2.5-21
ZDK2.5-22
ZDK2.5-22-BL
ZDK2.5-22-PE
ZDK2.5-D1
ZDK2.5-D1-PE
ZDK2.5-D2
ZDK2.5-D2-BL
ZDK2.5-D2-PE
ZDK4-22
ZDS4-22
ZDS4-22-R1
ZK10
ZK10-3P
ZK10-3P-BL
ZK10-3P-PV
ZK10-3P-PV-BL
ZK10-BL
ZK10-OR
ZK10-PE
ZK10-PE-3P
ZK10-PV
ZK10-PV-BL
ZK16
ZK16-3P
ZK16-3P-BL
ZK16-3P-PV
ZK16-3P-PV-BL
ZK16-BLZK16-PE
ZK16-PE-3P
ZK16-PV
ZK16-PV-BL
ZK2.5
ZK2.5-3P
ZK2.5-3P-BK
ZK2.5-3P-BL
ZK2.5-3P-GN
ZK2.5-3P-OR
ZK2.5-3P-RD
ZK2.5-3P-WH
ZK2.5-3P-YL
ZK2.5-4P

INDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKSPart Number
Part Number
1SNK508312R0000
1SNK508311R0000
1SNK508065R0000
1SNK508060R0000
1SNK531010R0000
1SNK531020R0000
1SNK531060R0000
1SNK510010R0000
1SNK510020R0000
1SNK510030R0000
1SNK510150R0000
1SNK536010R0000
1SNK536020R0000
1SNK536060R0000
1SNK512010R0000
1SNK512020R0000
1SNK512150R0000
1SNK512060R0000
1SNK516010R0000
1SNK516020R0000
1SNK516030R0000
1SNK516150R0000
1SNK516170R0000
1SNK505010R0000
1SNK505066R0000
1SNK505020R0000
1SNK505064R0000
1SNK505211R0000
1SNK505210R0000
1SNK505220R0000
1SNK505230R0000
1SNK505315R0000
1SNK508425R0000
1SNK508423R0000
1SNK508424R0000
1SNK505316R0000
1SNK505215R0000
1SNK505214R0000
1SNK505061R0000
1SNK505030R0000
1SNK505150R0000
1SNK506153R0000
1SNK505063R0000
1SNK508013R0000
1SNK506013R0000
1SNK505062R0000
1SNK505310R0000
1SNK505320R0000
1SNK506410R0000
1SNK508410R0000
1SNK508430R0000
1SNK508412R0000
1SNK508413R0000
1SNK508414R0000
1SNK508415R0000
1SNK508411R0000
1SNK506412R0000
1SNK506413R0000
1SNK506415R0000
1SNK506416R0000
1SNK506411R0000
1SNK505330R0000
1SNK505313R0000
1SNK506313R0000
1SNK505314R0000
1SNK506314R0000
1SNK506310R0000
1SNK506320R0000
1SNK506330R0000
1SNK506414R0000
1SNK508416R0000
1SNK508419R0000
1SNK505311R0000
1SNK505312R0000
1SNK506312R0000
1SNK505321R0000
1SNK505331R0000
1SNK506311R0000
1SNK506321R0000
1SNK506331R0000
1SNK505212R0000
1SNK506213R0000
1SNK505065R0000
1SNK505060R0000
1SNK516011R0000
1SNK516064R0000
1SNK516021R0000
1SNK516151R0000
1SNK516063R0000

Page
152
152
84
84
91
91
91
85
85
85
85
92
92
92
86
86
86
86
87
87
87
87
101
80
80
80
80
137
136
136
136
142
144
145
145
143
149
148
80
80
80
131
80
124
130
80
105
105
126
120
120
122
123
122
123
121
128
129
128
129
127
105
112
114
113
115
107
107
107
132
125
125
106
106
108
106
106
108
108
108
146
147
80
80
88
88
88
88
88

Index_1SNK160027C0206

7

Type

IndexType classification
Part Number

Page

ZS50-YL
ZS6
ZS6-3S
ZS6-3S-BL
ZS6-3S-PE
ZS6-3S-YL
ZS6-4S
ZS6-4S-BL
ZS6-4S-PE
ZS6-4S-YL
ZS6-BKZS6-BLZS6-BRZS6-D1ZS6-D1-PE
ZS6-D1-RD
ZS6-D2ZS6-D2-BK
ZS6-D2-BL
ZS6-D2-OR
ZS6-D2-PE
ZS6-D2-RD
ZS6-D2-WH
ZS6-D2-YL
ZS6-GNZS6-ORZS6-PEZS6-PRZS6-RDZS6-S
ZS6-S-4S-T2
ZS6-S-BL
ZS6-WHZS6-YL
ZS70
ZS70-BL
ZS70-PE
ZS70-YL
ZS95
ZS95-BL
ZS95-PE
ZS95-YL

1SNK516060R0000
1SNK506010R0000
1SNK506011R0000
1SNK506021R0000
1SNK506151R0000
1SNK506067R0000
1SNK506012R0000
1SNK506022R0000
1SNK506152R0000
1SNK506068R0000
1SNK506066R0000
1SNK506020R0000
1SNK506064R0000
1SNK506211R0000
1SNK506250R0000
1SNK506214R0000
1SNK506210R0000
1SNK506266R0000
1SNK506220R0000
1SNK506230R0000
1SNK506212R0000
1SNK506262R0000
1SNK506265R0000
1SNK506260R0000
1SNK506061R0000
1SNK506030R0000
1SNK506150R0000
1SNK506063R0000
1SNK506062R0000
1SNK506315R0000
1SNK506316R0000
1SNK506322R0000
1SNK506065R0000
1SNK506060R0000
1SNK522010R0000
1SNK522020R0000
1SNK522150R0000
1SNK522060R0000
1SNK526010R0000
1SNK526020R0000
1SNK526150R0000
1SNK526060R0000

88
81
82
82
82
82
83
83
83
83
81
81
81
139
138
139
138
138
138
138
140
138
138
138
81
81
81
81
81
109
110
109
81
81
89
89
89
89
90
90
90
90

Type

Part Number

Page

Type

Part Number

Page

7

Index_1SNK160027C0206

Type

PAGE 279

NotesINDUSTRIAL /// ENTRELEC - SNK TERMINAL BLOCKS

DEDICATED APPLICATIONSTERMINAL BLOCKS
IDC, spring loaded, stud, screw, spring,pluggable technologies
ENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSENTRELEC Terminal blocks
TE Connectivity proposes one of the largest
Din Rail Terminal block offering on themarket with various technologies: screw,
PI‑Spring, spring, IDC, pluggable, stud, etc.
found in over 8000 products & solutions.

You can access to more product details, use the order code or the product type in our web site: te.com
D2.5/5.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 5 mm 0.197 in spacing
Description– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,– Up to 2 wires per connection in the ADO System® connection.

Ordering details
1SNC163068F0014

Description

Color

Type

Part Number

D2.5/5.ADO
D2.5/5.N.ADO
D2.5/5.ADO

1SNA199554R2300
1SNA199556R2500
1SNA199555R2400

Grey
Blue
OrangeMain technical data

56 2.20"48.5 1.91"

Weight(1 pce) g
6.00
6.00
6.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

45 1.77"

50
50
50

2

CSA

Rail

0.2-1 mm²0.22-1 mm²

24-18 AWG
24-18 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-2.5 mm²

22-12 AWG

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.in

IEC
ADO

D2.5/5.ADO

Pkg
pce

Feed-throughUL

A3
13.5 A / 1 mm²
120 A1000 V
8000 V
IP20
NEMA 1

TH 35-7.5,
TH 35-15

Connect to

7 A / 18 AWG
600 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

23 0.91"

US

cCSAusGost R

5 mm 0.197 in spacing

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS
Accessories
Description

1

2

1
2
3

3

4

5

6

4
5
6

10 mm
0.394 in
5.2 mm0.205 in
3 mm
0.118 in
2 poles
24 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 0 mm
0 in
End stops

End sections
Jumper bars

Color

Dark grey
Grey

Grey

Grey

Type

Part Number

BAM4
BAZ1
FEDAD1
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
PC5-2
PC5-10EIPSCAD5

1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA199551R2000

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10

14.00
5.30
2.50
3.30
5.00
6.70
8.40
16.90
1.80
6.00
0.30

1SNC160065S0201

1 mm²
18 AWGDedicated applications
Terminal blocks
Connection devices offering

2

1

ADO System® IDC terminal blocks

112

Spring loaded screw clamp terminal blocks

59

3Stud terminal blocks

71

4

Ring lug terminal blocks

99

5

Miniblocks

109

6

Test & measurement terminal blocks

153

7

Pluggable terminal blocks

173

Sensors / Actuators terminal blocks

189

Installation terminal blocks

207

Protection terminal blocks

237

8

9

10

1SNC160065S0201

11

Disconnect terminal blocks

243

Component holder terminal blocks

251

Index		

265

12

13

14

1-1773977-3_EN - Edition February 2020
PAGE 1

ENTRELEC Terminal blocks

TE Connectivity proposes one of the largest Din Rail Terminal block offering on themarket with various technologies: screw, PI-Spring, spring, IDC, pluggable, stud, etc.
found in over 8000 products & solutions.

1

Scope

SNK
terminal blocks

Dedicated applications
terminal blocks

Terminal blocks forrailway applications

Qualified for worldwide applications andsevere environments (such as hazardous
locations, railways, marine and solar
applications..).
From 0.2 to 300 mm².

Specific terminal blocks and technologies
for dedicated applications and markets.

The largest offering on
the market for rollingstock and infrastructures.

Product
SNK PI-Springfamilies & technology
functions 2.5 to 16 mm²
12 to 4 AWG

Feed-throughMulti-deck
GroundDisconnect
for fuses
Component holder

ADO System® (IDC)
0.22 to 4 mm²
24 to 12 AWG

ADO-ADO or ADO-screw clamp SNK PI-Spring technology
Feed-through / Multi-deck /2.5 to 16 mm²Ground / Disconnect /12 to 4 AWG
for fuses / Component holder

Safety (spring loaded)
0.22 to 10 mm²
24 to 6 AWG

Feed-throughDisconnect
Test & measurement

SNK pluggablescrew & PI-Spring technologies
2.5 to 4 mm²
12 to 10 AWG

SNK screw clamp
technology
4 to 240 mm²
12 to 500 Kcmil

Feed-throughMulti-deck
GroundDisconnect
for fuses
Test & measurement
Marshalling
Component holderStud
25 to 300 mm²
4 AWG to 1000 Kcmil

One stud
2 studs
One stud - One screw clamp

ADO System® (IDC)
1.5 to 4 mm²
16 to 12 AWG

Ring lug
6 to 16 mm²
8 to 6 AWG

Feed-throughTest & measurementStud
4 to 185 mm²

SNK pluggablescrew & PI-Spring
technologies
2.5 to 4 mm²
12 to 10 AWG

Feed-throughMulti-deck
GroundMiniblocks
1.5 to 6 mm²
18 to 8 AWG

Screw clamp
SpringADO System ® (IDC)

Quick-connect
2.5 to 6 mm²

Other types
Test & measurement: with sliding link, blade, plug
Pluggable: feed-through, double deck, disconnect
Sensors/actuators: screw, spring, ADO system (IDC)
Installation: screw, spring
Protection: ground + neutral
Component holders: screw, spring, ADO system (IDC)

www.te.com

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSDBL power
distribution blocks

ESSAILEC®
test blocks

Interfast PLC
pre-wiring system

Marking
solutions

The preferred choice for primary
power distribution and solar
applications.

Test blocks for safe and easy
testing on secondary circuitsof current and voltage
transformers and sensors.

PLC pre-wiring system for fast,
flexible, reliable connection of PLC’sin process automation applications.

Markers & marking systems for
all identification requirements inelectrical panels.

From 80 A up to 550 A (IEC)

Current and voltage
sockets & plugs

Interfast PCB:
Compact & standard modules

Terminal block identification andgroup markers

Simultaneous testing of
1 to 4 independent circuitson the same socket

Interfast MS:
Modular system based onterminal block technology

Wire and cable identification

Terminal blocks types:
2 to 10 poles, up to 20 outputs

Component and equipment
identification

Several testing principle such
Functions:as “make before break” for safe – – 1 to 4 wire connections (sensors) Panel identification
current transformer testing– – Disconnect
Pre-printed markers for terminal– – Fuse
blocksPanel and switchboard
mounting : base, flush, rack,– – Signal indication
TH35 rail– – Relays
Multicircuits sockets & plugs– – Optocouplers– – Solenoid valve control– – Galvanic isolation (2.5 kV).

1SNC160261S0201

Modular blocks: single pole, three& four poles, up to 12 outputs

1

PAGE 3

Screw clamp technology
The heavy duty connection

Unique design, flies over time thanks to its reliability andsafetyThe TE Connectivity screw clamp technology is designed to
avoid accidental releases due to vibrations, shocks or evenabusive cable draw. Our exclusive design minimizes the needsof retightening campaigns.

High density capacity
The screw clamp technology can fit up to two conductors per
clamp which offers extended possibilities in electrical cabinets.

1

Features

The TE Connectivity exclusiveanti-release system creates acontrolled locking-screw effectthanks to the 2 overlapping tabs
that maintain the clamp parts.
The screw is locked in total safety.
The retightening campaigns are
not needed anymore!

The clamp is punched, which
increases the number of screw
threads by 30 % meaning ahigh torque resistance

Screw

Screw clamp
Hardened steel makes theconnection very reliable

Conductive
linking bar
Stripped wire

Flap avoiding the insertionof cable underneath theclamp

From 0.22 mm² up to 240 mm²
From 24 AWG up to 500 Kcmil

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

1SNC161117S0201

The screw tightens the
conductive bar to the cable.
There is no torsion effectapplied to the cableTE Connectivity spring loaded screw clamp technology
The safety connection for demanding working conditions

Exclusive design provide robustness and connection
safetyThe TE Connectivity screw clamp spring loaded terminal isdesigned to guarranty electrical continuity even when screw
are loosened unintentionally.
It features all the benefits of our screw clamp with additional
vibration,shock resistant and maintenance free performances.

High density wiring
The screw clamp spring loaded terminal can fit up to two conductors equipped with bent ferrules per clamp.

1

Features

The TE Connectivity exclusiveanti-release system createsa controlled locking-screw
effect thanks to the 2
overlapping tabs that maintainthe clamp parts. The screw
is locked in total safety. The
retightening campaigns are
not needed anymore!

The clamp is punched, which
increases the number of screw
threads by 30 % meaning ahigh torque resistance

Screw

Screw clamp
Conductive
linking bar
Stripped wire

Hook type ferrule
Provide pull-out
proof connection

Hardened steel makes theconnection very reliable

SpringPowerfull steel spring underneath
Clamp ensures pemanent contactpressure

The screw tightens the
conductive bar to the cable.
There is no torsion effectapplied to the cable

Flap avoiding the insertion of cable
underneath the clamp

Hook type ferrule

From 0.22 mm² up to 10 mm²
1SNC161123S0201_dupli

From 24 AWG up to 6 AWG

PAGE 5

TE Connectivity spring clamp technology

Experience the flexible connection
The TE Connectivity spring clamp technology combines all thefeatures appreciated from electrical users by combining flexibilityof use with front entry, a good vibration withstand, clamping
pressure non dependent on the operator and automatic creeping
compensation suppressing the needs of retightening campaigns.
1

Features

Design preventing incorrect conductor
insertion and damages to the connection

Specific hardened stainless steel
makes the connection very reliable
and corrosion resistantMaterial and shape of the spring
optimised to offer high limit ofelasticity
Clamping contact pressure non dependent on theoperator and automatic creeping compensation

From 0.12 mm² up to 35 mm²

1SNC162112S0201

From 26 AWG up to 2 AWG

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSADO System® IDC technology
The fastest and most reliable connection technology

ADO system ® is based on Insulation Displacement Connection(IDC) technology. IDC technology can be found in various
applications outside the electrical word. (RJ45 connectors
used in Telecom for instance).

Our ADO system® features one single piece which (whenassociated with its dedicated tool) combines the wire
preparation and the wire connection. Its design is made toconnect up to two conductors (standard wires as well as
special wires) in the same jaw.
1

FeaturesCorrosion proof
Gas-tight connection
Contact points arewrapped by
the insulation.

Contact lips:
allows the electricalcontact with a permanent
cable contact pressure

Low galvanic couple ofcopper alloy jaw pinching
the wire at two points.

Cone entry shape:
allows the insulation
cuttingVibration proof
Wire insulation ispinched by theinsulating body.

ADO system ® jaw:
"C shape" spring

Unstripping insulator
absorbs vibrations.

Contact forces arepermanently balanced.

Instructions:
1

2

3

4

Two
conductors

1 Insert the wire (not stripped) in the ADO System ® jaw until it butts.
2 Position the tool in the recess and pull the trigger fully and release it.
3 R emove the trigger. (the tool will not be released if the connection is not completed).

4 Follow the same process if a second wire has to beconnected (same size and same nature).
The first wire preliminary installed, will remain perfectly
and safely maintained in the clamp during the second wire
cabling process.

1SNC163080S0201_dupli

From 0.22 mm² up to 4 mm²
From 24 AWG up to 12 AWG

PAGE 7

TE Connectivity Stud technology
The connection for power and energy circuits

Reliability first
Stud technology is designed to ensure a reliable connection
thanks to the combination of:– – Vibration resistant equipments (nuts, washers),– – Lugs crimped on the cable provide pull-out proof
termination.

This technology is very popular on the American market andparticularly in the energy applications.

1

Available configurations

One stud

Two studs

One screw clamp / one stud

Connection technics

M4-M5
6 mm 28 AWG

M635 mm 21 AWG

M8
70 mm 2000 AWG

M10
120 mm 2
300 Kcmil

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

M12
185 mm 2
500 Kcmil

M16
300 mm 2
1 000 Kcmil

1SNC165028S0201_dupli

Up to 300 mm² / 1 000 Kcmil

1

PAGE 9

1SNC163102S0201

2

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
ADO System® IDC technology
Technologies presentation		

12

Overview			

14

ADO / screw clamp		
Feed-through		
1 mm² / 18 AWG

D2.5/5.ADO		

17

1.5 mm² / 16 AWG

D4/6.ADO		

18

2.5 mm² / 14 AWG

D6/8.ADO		

20

4 mm² / 12 AWG

D6/8.ADO3		

22

Ground		
1 mm² / 18 AWG

D2.5/5.P.ADO		

1.5 mm² / 16 AWG

D4/6.P.ADO		

23
24

2.5 mm² / 14 AWG

D6/8.P.ADO		

25

4 mm² / 12 AWG

D6/8.P.ADO3		

26

2

Double deck		
1.5 mm² / 16 AWG

D4/6.D2.ADO		

27

2.5 mm² / 14 AWG

D6/8.D2.ADO		

28

Disconnect with blade		
1 mm² / 18 AWG

D2.5/5.SN.ADO		

1.5 mm² / 16 AWG

D4/6.SN.ADO		

29
31

2.5 mm² / 14 AWG

D4/8.SN.ADO		

33

For 5 x 20 and 5 x 25 mm fuse (0.197 x 0.787 in and 0.197 x 0.984 in)		
1.5 mm² / 16 AWG

D4/8.SF...I.ADO		

34 to 36

2.5 mm² / 14 AWG

D4/8.SF...I.ADO2		

37 to 38

Disconnect with lever		
1.5 mm² / 16 AWG

D4/8.SN...I.ADO		

39

2.5 mm² / 14 AWG

D4/8.SN...I.ADO2		

40

ADO / ADO		
Feed-through		
1 mm² / 18 AWG

D1/5.ADO		

41

1.5 mm² / 16 AWG

D1.5/6.ADO		

42

2.5 mm² / 14 AWG

D2.5/8.ADO		

43

4 mm² / 12 AWG

D4/8.ADO		

44

Ground		
1 mm² / 18 AWG

D1/5.P.ADO		

45

1.5 mm² / 16 AWG

D1.5/6.P.ADO		

46

2.5 mm² / 14 AWG

D2.5/8.P.ADO		

47

4 mm² / 12 AWG

D4/8.P.ADO		

48

Double deck		
1.5 mm² / 16 AWG

D1.5/6.D2.ADO		

49

Disconnect with blade		
1 mm² / 18 AWG

D1/5.SNT2.ADO		

1.5 mm² / 16 AWG

D1.5/6.SNT2.ADO		

50
51

2.5 mm² / 14 AWG

D2.5/8.SNT2.ADO		

52

1.5 mm² / 16 AWG

D1.5/8.SF.ADO		

53 to 54

2.5 mm² / 14 AWG

D2.5/8.SF.ADO2		

55 to 56

Disconnect with lever		
2.5 mm² / 14 AWG

D4/8.SNNT.ADO2		

57

PAGE 111SNC163102S0201

For 5 x 20 and 5 x 25 mm fuse (0.197 x 0.787 in and 0.197 x 0.984 in)		

Dedicated applications terminal blocks
ADO System® IDC technology

Rely on our expertise

With ADO System®, TE Connectivity is
the leader
in IDC technology since 25 years.
More than 4000 customers worldwide
are using this technology with sucess
in the most severe environments.
2

Qualified for worldwide markets and applications
Eco-designed according to international environmental
standards in sustainable development.

RoHS

ISO 9001

Experience the fastest and the most reliable connection
on the market
Secure your connection process
Tool is locked on terminal block during all connection process. The conductor requires no preparation (no stripping,no ferrule). Maintenance free (screwless connection).
No fatigue thanks to the use of automatic tool.
Well adapted to special cables.

Trust ADO System® reliability in any environments
ADO System ® technology provides superior performances
and is the best solution for installations with severe constraints (continuity of service, clearance for work) as well as
strong environmental requirements (vibrations,corrosion)
This is the reason why today ADO System® is successfully
used in chemical/petrochemical, traction, waste water
treatment environments.

Connection process secured:
Tool locked on terminal blocks, high speed connection

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

1SNC163079S0201

Speed up your wiring process and reduce time to market!
Reduce wiring time up to 80 % compare to a screw connection with ferrules.
High speed Connection process: less than 3 seconds!
No preparation of cable, no tightening, no use of ferrules.
Pneumatic tool available for even faster process.

ADO System® IDC technology
The fastest and most reliable connection technology
ADO System® is based on Insulation Displacement Connection (IDC) technology. IDC technology can be found in various
applications outside the electrical word. (RJ45 connectors
used in Telecom for instance).

Our ADO System® features one single piece which (whenassociated with its dedicated tool) combines the wire preparation and the wire connection. Its design is made to connect
up to two conductors (standard wires as well as special wires)in the same jaw.

FeaturesCorrosion proof
Gas-tight connection
Contact points arewrapped by
the insulation.

Contact lips:
allows the electricalcontact with a permanent
cable contact pressure2

Low galvanic couple ofcopper alloy jaw pinching
the wire at two points.

Cone entry shape:
allows the insulation
cuttingVibration proof
Wire insulation ispinched by theinsulating body.

ADO System ® jaw:
"C shape" spring

Unstripping insulator
absorbs vibrations.

Contact forces arepermanently balanced.

Instructions:
1

2

3

4

Two
conductors

1 Insert the wire (not stripped) in the ADO System ® jaw until it butts.
2 Position the tool in the recess and pull the trigger fully and release it.
3 Remove the trigger. (the tool will not be released if the connection is not completed).

4 Follow the same process if a second wire has to beconnected (same size and same nature).
The first wire preliminary installed, will remain perfectly
and safely maintained in the clamp during the second wire
cabling process.

1SNC163080S0201

From 0.22 mm² up to 4 mm²
From 24 AWG up to 12 AWG

PAGE 13

Dedicated applications terminal blocks
ADO System® IDC technology

ADO / screw clamp

Feed-through2

GroundDouble deck

SectionIEC

UL/CSA*

1 mm²
1.5 mm²
2.5 mm²
4 mm²

18 AWG
16 AWG
14 AWG
12 AWG

D2.5/5.ADO
D4/6.ADO
D6/8.ADO
D6/8.ADO3

5 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 in
8 mm 0.315 in

D2.5/5.P.ADO
D4/6.P.ADO
D6/8.P.ADO
D6/8.P.ADO3

5 mm 0.197 in

D4/6.D2.ADO
D6/8.D2.ADO

6 mm 0.236 in
8 mm 0.315 in

6 mm 0.236 in
8 mm 0.315 in

8 mm 0.315 in(*) For indication only, refer to product page for certified crosse section.

ADO / ADO

Feed-throughGroundDouble deck

SectionIEC

UL/CSA*

1 mm²
1.5 mm²
2.5 mm²
4 mm²

18 AWG
16 AWG
14 AWG
12 AWG

D1/5.ADO
D1.5/6.ADO
D2.5/8.ADO
D4/8.ADO

5 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 in
8 mm 0.315 in

D1/5.P.ADO
D1.5/6.P.ADO
D2.5/8.P.ADO
D4/8.P.ADO

5 mm 0.197 in

D1.5/6.D2.ADO

6 mm 0.236 in

6 mm 0.236 in

8 mm 0.315 in
8 mm 0.315 in(*) For indication only, refer to product page for certified crosse section.

Miniblocks

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pluggable

1SNC163081S0201

Complementary functions: see related chapters in this catalog

Disconnect with blade2

5 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 inDisconnect with blade

D1/5.SNT2.ADO
D1.5/6.SNT2.ADO
D2.5/8.SNT2.ADO

Disconnect with leverD4/8.SF...I.ADO
D4/8.SF...I.ADO2

8 mm 0.315 in
8 mm 0.315 inFuse

D4/8.SN...I.ADO
D4/8.SN...I.ADO2

8 mm 0.315 in
8 mm 0.315 inDisconnect with lever

5 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 inSensors / actuators

D1.5/8.SF.ADO
D2.5/8.SF.ADO2

8 mm 0.315 in
8 mm 0.315 in

D1.5/8.SNN.ADO
D2.5/8.SNNT.ADO2

8 mm 0.315 in
8 mm 0.315 in

1SNC163081S0201

D2.5/5.SN.ADO
D4/6.SN.ADO
D4/8.SN.ADO

FuseComponent holders

PAGE 15

2

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/5.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 5 mm 0.197 in spacing
1 mm²
18 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
1SNC163068F0014

Description

Color

Type

Part Number

Feed-through

Grey
Blue
OrangeD2.5/5.ADO
D2.5/5.N.ADO
D2.5/5.ADO

1SNA199554R2300
1SNA199556R2500
1SNA199555R2400

ADO

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

56 2.20"48.5 1.91"

50
50
50

2

CSA

Rail

TH 35-7.5,
TH 35-15

0.2-1 mm²0.22-1 mm²

24-18 AWG
24-18 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-2.5 mm²

22-12 AWG

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.inIEC

45 1.77"

Weight(1 pce) g
6.00
6.00
6.00

pce

Main technical data

D2.5/5.ADO

Pkg

UL

A3
13.5 A / 1 mm²
120 A1000 V
8000 V
IP20
NEMA 17 A / 18 AWG
600 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

23 0.91"

US

cCSAusGost R

5 mm 0.197 in spacing

Accessories
Description
2

1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
24 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 0 mm
0 in
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

Grey

White

Type
BAM4
BAZ1
FEDAD1
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
PC5-2
PC5-10
EIP
SCAD5
CBM5
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA199551R2000
1SNA178745R1400
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
50
1
1
1

14.00
5.30
2.50
3.30
5.00
6.70
8.40
16.90
1.80
6.00
0.30
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D2.5/5.ADO

Green-yellow

TypeD2.5/5.P.ADO

Part Number
1SNA399030R0500

Pkg

Weightpce(1 pce) g

50

9.00

Technical data valid for copper conductors only.

PAGE 17

1SNC163001S0201 - Rev. A

1

Color

D4/6.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163061F0014

pce

Feed-through

Grey
Blue
OrangeADO

56 2.20"48.5 1.91"

50
50
50

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

45 1.77"

1SNA199034R1500
1SNA199036R1700
1SNA199035R1600

Main technical data

2

D4/6.ADO

D4/6.ADO
D4/6.N.ADO
D4/6.ADO

Weight(1 pce) g
7.00
7.00
7.00

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²22-10 AWG

22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
17.5 A / 1.5 mm² 18 A / 16 AWG 18 A / 16 AWG
180 A
1000 V
600 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

USR CNRUS

cCSAusGost R

23 0.91"

6 mm 0.236 in spacing

Accessories
Description
2

1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
35 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 0 mm
0 in
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

Grey

White

Type
BAM4
BAZ1
FEDAD1BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
PC6-2
PC6-10
EIP
SCAD
CBM5
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA113546R1400
1SNA113548R2600
1SNA113550R2400
1SNA196896R0000
1SNA178745R1400
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
50
1
1
1

14.00
5.30
2.50
4.40
6.70
8.90
11.20
22.40
2.00
8.00

205.00
29.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D4/6.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeD4/6.P.ADO

Part Number
1SNA199050R0100

Pkg

Weightpce(1 pce) g

50

11.00

1SNC163002S0201 - Rev. A

1

Color

D4/6.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²

With test socket DIA 2 mm 0.079 in

16 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

Feed-through56 2.20"48.5 1.91"

45 1.77"

With test socket
DIA 2 mm 0.079 in

Grey

Main technical data
Rated voltage
Impulse withstand voltage
Protection

IEC
800 V
8000 VIP20

D4/6.ADO.2
UL
600 V

1SNA199064R2300
CSA
600 V

50

Weight(1 pce) g
8.00

Nota

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

2

23 0.91"C

USR CNRRoHS

US

cCSAusGost R

Accessories
6 mm 0.236 in spacing

Description

Color

Type

Part Number

Pkg
pce

1

DIA 2 mm 0.079 in

Test plugs

Black

FC2

1SNA007865R2600

100

Part Number

Pkg

Weight(1 pce) g

1

1.5 mm²

With test socket DIA 4 mm 0.157 in

16 AWG

Ordering details
Description

Color

Type

pce

Feed-through56 2.20"48.5 1.91"

45 1.77"

With test socket
DIA 4 mm 0.157 in

Grey

Main technical data
Rated voltage
Impulse withstand voltage
Protection

IEC
800 V
8000 VIP10

D4/6.ADO.4
UL
600 V

1SNA199048R0300
CSA
600 V

50

Weight(1 pce) g
8.00

Nota

NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
23 0.91"CRoHS

USR CNRUS

cCSAusGost R

Accessories
6 mm 0.236 in spacing

Description
1

Test plugs

Color
DIA 4 mm 0.157 in

White

Type
FC4

Part Number
1SNA167860R0100

Pkg

Weightpce(1 pce) g

10

10.00

1SNC163003S0201 - Rev. A

1

Technical data valid for copper conductors only.

PAGE 19

D6/8.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
1SNC163065F0014

Description

Color

Type

Part Number

Feed-throughWith black marking forwire size 1-2.5 mm²(16-14 AWG)

D6/8.ADO
D6/8.N.ADO
D6/8.ADO

Grey
Blue
Orange1SNA199042R2500
1SNA199044R2700
1SNA199043R2600

Main technical data

ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

56 2.20"48.5 1.91"

45 1.77"50
50
50

Weight(1 pce) g
11.00
11.00
11.00

Mounting instructions2

D6/8.ADO

Pkg
pce

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

16-14 AWG

16-14 AWG

Wire stripping
length

12 mm
0.47 in0.2-10 mm²
0.22-6 mm²

22-8 AWG

22-8 AWG

Tool

Flat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in

Torque0.8 - 1 N.m
7.1 - 8.9 lb.in

A5
24 A / 2.5 mm² 25 A / 14 AWG 25 A / 14 AWG
300 A
1000 V
600 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

23 0.91"

USR CNRUS

cCSAusGost R

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

4
5

7

8

6
7
8

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
41 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
50 A
10 polesCross spacing
5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 injumpers
Universal screw jumper bar kit N°I
Universal screw jumper bar kit N°III
Circuit separators 0 mm
0 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

White

Type
BAM4
BAZ1
FEDAD1
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
PC8-2
PC8-10
EL6
BJDP1
BJDP3
SCAD
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA116538R1700
1SNA163313R2400
1SNA173627R2100
1SNA179623R0300
1SNA179625R0500
1SNA196896R0000
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
2.50
4.50
6.00
10.00
12.22
20.00
3.00
14.00
0.10
7.00
5.00
205.00
29.00
8.20

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D6/8.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeD6/8.P.ADO

Part Number
1SNA199118R2600

Pkg

Weightpce(1 pce) g

50

14.00

1SNC163004S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

D6/8.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²

With test socket DIA 2 mm 0.079 in

14 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

Feed-through56 2.20"48.5 1.91"

45 1.77"

23 0.91"

With test socket
DIA 2 mm 0.079 inand black marking forwire size 1-2.5 mm²(16-14 AWG)

Grey

Main technical data
Rated voltage
Impulse withstand voltage
Protection

IEC1000 V
8000 VIP20

D6/8.ADO.2

UL
600 V

1SNA199155R2300

CSA
600 V

50

Weight(1 pce) g
12.00

Nota

NEMA 1

2

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

8 mm 0.315 in spacing

USR CNRRoHS

US

cCSAusGost R

Accessories
Description

1

Color

Type

Part Number

Pkg
pce

1

DIA 2 mm 0.079 in

Test plugs

Black

FC2

2.5 mm²

With test socket DIA 4 mm 0.157 in

14 AWG

Ordering details
Description

Color

Type

1SNA007865R2600

100

Part Number

Pkg
pce

Feed-through56 2.20"
23 0.91"

48.5 1.91"

45 1.77"

With test socket
DIA 4 mm 0.157 inand black marking forwire size 1-2.5 mm²(16-14 AWG)

Grey

Main technical data
Rated voltage
Impulse withstand voltage
Protection

IEC
800 V
8000 VIP10

D6/8.ADO.4

UL
600 V

1SNA199157R2500

CSA
600 V

50

Weight(1 pce) g

Weight(1 pce) g
12.00

Nota

NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

8 mm 0.315 in spacingRoHS

USR CNRUS

cCSAusGost R

Accessories
Description

1

Test plugs

DIA 4 mm 0.157 in

White

Type
FC4

Part Number
1SNA167860R0100

Pkg

Weightpce(1 pce) g

10

10.00

1SNC163005S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 21

D6/8.ADO IDC terminal blocks
Feed-through ADO - screw clamp - 8 mm 0.315 in spacing
4 mm²
12 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163074F0014

pce

Feed-throughWith white marking
for wire size
4 mm2 (12 AWG)

D6/8.ADO3
D6/8.N.ADO3
D6/8.ADO3

Grey
Blue
OrangeMain technical data

Mounting instructions

2

ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

56 2.20"48.5 1.91"

45 1.77"

50
50
50

CSA

Rail

TH 35-7.5,
TH 35-15

4 mm²
4 mm²

12 AWG
12 AWG

Wire stripping
length

12 mm
0.47 in0.2-10 mm²
0.22-6 mm²

22-8 AWG

Tool

Flat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in

Torque0.8 - 1 N.m
7.1 - 8.9 lb.inIEC

D6/8.ADO

1SNA399245R1500
1SNA399319R1700
1SNA399800R1700

Weight(1 pce) g
11.00
11.00
11.00

UL

A5
32 A / 4 mm²
480 A
1000 V
8000 V
IP20

25 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

23 0.91"

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

4
5

7

8

6
7
8

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
41 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
50 A
10 polesCross spacing
Universal screw jumper bar kit N°I
jumpers
Universal screw jumper bar kit N°III
Circuit separators 0 mm
0 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

White

Type
BAM4
BAZ1
FEDAD1
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
PC8-2
PC8-10
BJDP1
BJDP3
SCAD
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA116538R1700
1SNA163313R2400
1SNA179623R0300
1SNA179625R0500
1SNA196896R0000
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
2.50
4.50
6.00
10.00
12.22
20.00
3.00
14.00
7.00
5.00
205.00
29.00
8.20

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D6/8 ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeD6/8.P.ADO3

Part Number
1SNA399251R1300

Pkg

Weightpce(1 pce) g

50

14.00

1SNC163006S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

D2.5/5.P.ADO IDC terminal blocks
Ground ADO - screw clamp - 5 mm 0.197 in spacing
1 mm²

1SNC163099F0014

18 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

pce

GroundScrewless rail connection Green-yellow

D2.5/5.P.ADO

1SNA399030R0500

Main technical data

ADO

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
Rated short-time withstand current (1s)Protection
Screw clamp

56 2.20"48.5 1.91"

50 1.97"50

Weight(1 pce) g
9.00

CSA

Rail

TH 35-7.5,
TH 35-15

0.2-1 mm²0.22-1 mm²

24-18 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-2.5 mm²

22-12 AWG

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.inIEC
D2.5/5.P.ADO

Pkg

A3
1 mm²
120 A
IP20

UL

2

18 AWG
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

25 0.98"

RoHS

US

cCSAusGost R

5 mm 0.197 in spacing

Accessories
Description
1

2

1
2
3

4

4

Dark grey
Grey

White

Type
BAM4
BAZ1
FEDAD1
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163009S0201 - Rev. A

3

10 mm 0.394 in
5.2 mm 0.205 in
End sections
3 mm 0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

End stops

Color

Technical data valid for copper conductors only.

PAGE 23

D4/6.P.ADO IDC terminal blocks
Ground ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²

1SNC163064F0014

16 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

GroundScrewless rail connection Green-yellow

D4/6.P.ADO

1SNA199050R0100

Main technical data

2

ADO

D4/6.P.ADO

56 2.20"48.5 1.91"

50

Weight(1 pce) g
11.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
Rated short-time withstand current (1s)Protection
Screw clamp

50 1.97"

Pkg
pce

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²22-10 AWG

22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

16 AWG

16 AWG
Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
1.5 mm²
180 A
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

25 0.98"RoHS

USR CNRUS

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

3

4

4

10 mm 0.394 in
5.2 mm 0.205 in
End sections
3 mm 0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

End stops

Color
Dark grey
Grey

White

Type
BAM4
BAZ1
FEDAD1
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
7.50

1SNC163010S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD6/8.P.ADO IDC terminal blocks
Ground ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²

1SNC163135F0014

14 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

pce

GroundScrewless rail connection, Green-yellow
with black marking forwire size 1-2.5 mm²(16-14 AWG)

D6/8.P.ADO

1SNA199118R2600

ADO

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
Rated short-time withstand current (1s)Protection

56 2.20"48.5 1.91"

Screw clamp

25 0.98"50

Weight(1 pce) g
14.00
2Main technical data
D6/8.P.ADO

50 1.97"

Pkg

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

16-14 AWG

16-14 AWG

Wire stripping
length

12 mm
0.47 in0.2-10 mm²
0.22-6 mm²

22-8 AWG

22-8 AWG

Tool

Flat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in

14 AWG

14 AWG
Torque0.8 - 1 N.m
7.1 - 8.9 lb.in

A5
2.5 mm²
300 A
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

8 mm 0.315 in spacing

USR CNRUS

cCSAusGost R

Accessories
Description
1

2

1
2
3

4

4

Dark grey
Grey

White

Type
BAM4
BAZ1
FEDAD1
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163011S0201 - Rev. A

3

10 mm
0.394 in
5.2 mm 0.205 in
End sections
3 mm
0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

End stops

Color

Technical data valid for copper conductors only.

PAGE 25

D6/8.P.ADO IDC terminal blocks
Ground ADO - screw clamp - 8 mm 0.315 in spacing
4 mm²
12 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp.

1SNC163101F0014

Ordering details

2

Description

Color

Type

Part Number

GroundScrewless rail connection, Green-yellow
with white marking
for wire size
4 mm² (12 AWG)

D6/8.P.ADO3

1SNA399251R1300

Main technical data

ADO

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
Rated short-time withstand current (1s)Protection
Screw clamp

56 2.20"
25 0.98"

48.5 1.91"

50 1.97"50

Weight(1 pce) g
14.00

CSA

Rail

TH 35-7.5,
TH 35-15

4 mm²
4 mm²

12 AWG

Wire stripping
length

12 mm
0.47 in0.2-10 mm²
0.22-6 mm²

22-8 AWG

Tool

Flat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in

Torque0.8 - 1 N.m
7.1 - 8.9 lb.inIEC
D6/8.P.ADO

Pkg
pce

A5
4 mm²
480 A
IP20

UL

12 AWG
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

4

10 mm
0.394 in
5.2 mm 0.205 in
End sections
3 mm
0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

End stops

Color
Dark grey
Grey

White

Type
BAM4
BAZ1
FEDAD1
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199336R2000
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
8.20

1SNC163012S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.D2.ADO IDC terminal blocks
Double deck ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– Save space with 2 decks terminal block,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163035F0014

Ordering details
Description

Color

Type

Part Number

Feed-throughWith 2 feed-throughcircuits

Grey
Blue

D4/6.D2.ADO
D4/6.D2.N.ADO

1SNA199242R0200
1SNA199244R0400

ADO

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

83 3.27"75.5 2.97"

50
50

2

CSA

Rail

TH 35-7.5,
TH 35-15

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC85.3 3.36"

Weight(1 pce) g
18.00
18.00

pce

Main technical data

D4/6.D2.ADO

Pkg

UL

A4
17.5 A / 1.5 mm²
180 A
800 V
6000 V
IP20
NEMA 1

18 A / 16 AWG
600 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

44.8 1.76"

RoHS

US

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

3

2

1
2
3

4
4

5

7

6

8

5
6
7
8
9

Color

10 mm
0.394 in
5 mm
0.197 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
35 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 0 mm
0 in
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

Grey

Grey

White

Type
BAZH1
FED2AD1
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
PC6-2
PC6-10
EIP
SCAD
CBD2S
OUPAD
OUMAD
RC610

Part Number
1SNK900102R0000
1SNA199417R1200
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA113546R1400
1SNA113548R2600
1SNA113550R2400
1SNA196896R0000
1SNA178408R1400
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
10
10
50
1
1
1

24.00
6.60
4.40
6.70
8.90
11.20
22.40
2.00
8.00

205.00
29.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

GroundDescription
GroundColor
Profile aligned with D4/6.D2 ADO

Green-yellow

TypeD4/6.D1.P.ADO

Part Number
1SNA399931R2500

Pkg

Weightpce(1 pce) g

50

23.00

Technical data valid for copper conductors only.

PAGE 27

1SNC163007S0201 - Rev. A

9

D6/8.D2.ADO IDC terminal blocks
Double deck ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²

Description–– Save space with 2 decks terminal block,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163102F0014

Ordering details
Description

Color

Type

Part Number

Feed-throughWith 2 feed-throughcircuits

Grey

D6/8.D2.ADO

1SNA399600R2600

Main technical data

2

ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

83 3.27"75.5 2.97"

85.3 3.36"

Weight(1 pce) g

50

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

Wire stripping
length

12 mm
0.47 in0.2-10 mm²
0.22-6 mm²

Tool

Flat screwdriverØ 4-4.5 mm
Ø 0.157 - 0.177 in

A5
24 A / 2.5 mm²
300 A
800 V
8000 V
IP20
NEMA 1Torque0.8 - 1 N.m
7.1 - 8.9 lb.inIEC
D6/8.D2.ADO

Pkg
pce

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.8 1.76"

RoHS

Gost R

8 mm 0.315 in spacing

Accessories
Description
1

3

2

1
2
3

4
4

5

6

5
6

10 mm
0.394 in
5 mm
0.197 in
2 poles
41 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars
2 poles
50 A
10 polesTools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

Grey

White

Type
BAZH1
FED2AD1
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
PC8-2
PC8-10
OUPAD
OUMAD
RC810

Part Number
1SNK900102R0000
1SNA199417R1200
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA116538R1700
1SNA163313R2400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1
1
1

24.00
6.60
4.50
6.00
10.00
12.22
20.00
3.00
205.0029.00
8.20

1SNC163008S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/5.SN.ADO IDC terminal blocks
Disconnect with blade - with test socket - ADO screw clamp 5 mm 0.197 in spacing
1 mm²

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163072F0014

Ordering details
Description

Color

Type

Part Number

pce

Disconnect

With test socket
DIA 2 mm 0.079 inon the ADO side

Grey

D2.5/5.SN.ADO

1SNA399226R0200

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

72 2.83"

64.5 2.54"

52 2.05"

59.5 2.34"

55 2.16"50

Weight(1 pce) g
9.00

Mounting instructions

2

Rail

TH 35-7.5,
TH 35-15

0.2-1 mm²0.22-1 mm²Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-2.5 mm²

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

A3
10 A / 1 mm²
120 A
320 V
4000 V
IP20

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.inIEC
D2.5/5.SN.ADO

Pkg

UL

CSA

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
23 0.91"
RoHS

Gost R

5 mm 0.197 in spacing

Accessories
1

Description

2
1

End stops

2 mm
0.079 in
2 poles 13.5 A
3 poles
5 poles
10 poles
Lateral jumper bars 2 poles 30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Test plugs
DIA 2 mm 0.079 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

3

4

2
3

5

6

4

8

5
6
7
8

End stops

End sections
Jumper bars

Dark grey
Grey
Orange

Grey

Black

White

Type
BAM4
BAZ1
FEDAD4BJADO5-2
BJADO5-3
BJADO5-5
BJADO5-10
PC5-2
PC5-10
EIP
FC2
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199352R0000
1SNA205955R0300
1SNA205956R0400
1SNA205958R1600
1SNA205963R0300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
20
20
20
10
10
10
10
100
1
1
1

14.00
5.30
2.30
1.00
1.00
2.00
5.00
1.80
6.00
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163013S0201 - Rev. A

7

Color

Technical data valid for copper conductors only.

PAGE 29

D2.5/5.SN.ADO IDC terminal blocks
Disconnect with blade - with test socket - ADO screw clamp 5 mm 0.197 in spacing
1 mm²

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163072F0014

Ordering details
Description

Color

Type

Part Number

Disconnect

With 2 test sockets
DIA 2 mm 0.079 inGrey

D2.5/5.SNT2.ADO

Main technical data

2

ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

72 2.83"

64.5 2.54"

52 2.05"

59.5 2.34"

55 2.16"

1SNA399228R1400

50

Weight(1 pce) g
9.00

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

0.2-1 mm²0.22-1 mm²Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-2.5 mm²

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

A3
10 A / 1 mm²
120 A
320 V
4000 V
IP20

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.inIEC
D2.5/5.SN.ADO

Pkg
pce

UL

CSA

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

23 0.91"

Gost R

5 mm 0.197 in spacing

Accessories
Description
1

2

1
2
3

3

4
4

5

6

5
6
7
8

8

Dark grey
Grey
Orange

Grey

Black

White

Type
BAM4
BAZ1
FEDAD4BJADO5-2
BJADO5-3
BJADO5-10
PC5-2
PC5-10
EIP
FC2
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199352R0000
1SNA205955R0300
1SNA205956R0400
1SNA205963R0300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
10
10
10
100
1
1
1

14.00
5.30
2.30
1.00
1.00
5.00
1.80
6.00
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163014S0201 - Rev. A

7

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2 mm
0.079 inJumper bars
2 poles13.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Test plugs
DIA 2 mm 0.079 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.SN.ADO IDC terminal blocks
Disconnect with blade - with test socket - ADO screw clamp 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163072F0014

Ordering details
Description

Color

Type

Part Number

Disconnect

ADO

With test socket
DIA 2 mm 0.079 inon the ADO side

Grey
OrangeD4/6.SN.ADO
D4/6.SN.ADO

1SNA199107R2400
1SNA199108R0500

72 2.83"

64.5 2.54"

52 2.05"

59.5 2.34"

50
50

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

55 2.16"Weight(1 pce) g
9.00
9.00

pce

Main technical data
D4/6.SN.ADO

Pkg

2

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²22-10 AWG

22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
10 A / 1.5 mm² 10 A / 16 AWG 15 A / 16 AWG
180 A
500 V
600 V
600 V
6000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
23 0.91"CRoHS

USR CNRUS

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

3

5

4

6

4
5
6
7

10 mm
0.394 in
5.2 mm 0.205 in
End sections
2 mm
0.079 inJumper bars
2 poles17.5 A
3 poles
10 poles
Lateral jumper bars
10 poles 35 A
Test plugs
DIA 2 mm 0.079 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color
Dark grey
Grey
Orange

Black

White

Type
BAM4
BAZ1
FEDAD4BJADO6-2
BJADO6-3
BJADO6-10
PC61-10
FC2
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199352R0000
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA163311R2200
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
10
100
1
1
1

14.00
5.30
2.30
1.00
1.00
6.00
5.00
205.00
29.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163015S0201 - Rev. A

7

Technical data valid for copper conductors only.

PAGE 31

D4/6.SNT2.ADO IDC terminal blocks
Disconnect with blade - with test socket - ADO screw clamp 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163033F0014

Ordering details
Description

Color

Type

Part Number

pce

Disconnect

With 2 test sockets
DIA 2 mm 0.079 inGrey

D4/6.SNT2.ADO

1SNA199235R2300

Main technical data

2

ADO

D4/6.SNT2.ADO

72 2.83"

64.5 2.54"

52 2.05"

59.5 2.34"50

Weight(1 pce) g
9.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

55 2.16"

Pkg

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²22-10 AWG

22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
10 A / 1.5 mm² 10 A / 16 AWG 15 A / 16 AWG
180 A
500 V
600 V
600 V
6000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

23 0.91"RoHS

USR CNRUS

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5
6

Lateral jumper bars
Test plugs
Tools

7

Terminal block markers

4

6

Color
10 mm 0.394 in
5.2 mm 0.205 in
2 mm
0.079 in
2 poles 17.5 A
3 poles
10 poles10 poles 35 A
DIA 2 mm 0.079 in
Semi automatic tool
Hand tool
Blank card

Dark grey
Grey
Orange

Black

White

Type
BAM4
BAZ1
FEDAD4BJADO6-2
BJADO6-3
BJADO6-10
PC61-10
FC2
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199352R0000
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA163311R2200
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
10
100
1
1
1

14.00
5.30
2.30
1.00
1.00
6.00
5.00
205.00
29.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163016S0201 - Rev. A

7

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/8.SN.ADO IDC terminal blocks
Disconnect with blade - with test socket - ADO screw clamp 8 mm 0.315 in spacing
2.5 mm²
16 AWG

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163087F0014

Ordering details
Description

Color

Part Number

Disconnect

ADO
55 2.16"

With test socket
DIA 2 mm 0.079 in on
the ADO side,with black marking forwire size 1-2.5 mm²(16-14 AWG)

Grey

D4/8.SN.ADO

1SNA199137R1100

72 2.83"

64.5 2.54"

52 2.05"50

Weight(1 pce) g
11.00

2

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

23 0.91"

Pkg
pce

Main technical data

D4/8.SN.ADO

59.5 2.34"

Type

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length

9.5 mm0.37 in

0.2-6 mm²0.22-4 mm²22-10 AWG

22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
15 A / 2.5 mm² 15 A / 16 AWG 15 A / 16 AWG
300 A
500 V
600 V
600 V
6000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

C

RoHS

USR CNRUS

cCSAusGost R

Accessories
Description
1

3

2

4

1
2
3
4
5
6

6

Dark grey
Grey
Black

White

Type
BAM4
BAZ1
FEDAD4
PC81-10
FC2
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199352R0000
1SNA173523R1100
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
1
1
1

14.00
5.30
2.30
5.00
205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163017S0201 - Rev. A

5

10 mm 0.394 in
5.2 mm 0.205 in
End sections
2 mm
0.079 in
Lateral jumper bars
10 poles 35 A
Test plugs
DIA 2 mm 0.079 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 33

D4/8.SF.I.ADO IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket ADO - screw clamp 8 mm 0.315 in spacing
1.5 mm²

Description–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not delivered with the terminal blocks),–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163110F0014

Ordering details
Description

Color

Type

Part Number

Fuse

With test socket
DIA 2 mm 0.079 inon the ADO side

D4/8.SF.I.ADO

Grey

1SNA399785R0300

Main technical data

2
D4/8.SF.I.ADO

ADO

55.9 2.20"

48.4 1.90"

94 3.70"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

180°

86.5 3.40"

Rigid: Solid/Stranded
Flexible without ferrule

50

Weight(1 pce) g
13.00

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
6.3 A / 1.5 mm²
180 A
630 V
8000 V
IP20
NEMA 1Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC68.2 2.68"

Pkg
pce

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

25.5 1.00"

RoHS

Gost R

8 mm 0.315 in spacing

Accessories
Description
2

3

4

5

6

7

8

1

End stops

23
4
5

End sections
Lateral jumper bars
Test plugs
Fuses

6

Assembly rods

7
8

Spring retaining rings
Tools

9
9

10 mm 0.394 in
5.2 mm 0.205 in
1.5 mm 0.059 in
10 poles 35 A
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
FU520

TGA8

Semi automatic tool
Hand tool
Terminal block markers Blank card

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC terminal blocks
Description
Disconnect

Color
Profile aligned with D4/8.SF...ADOTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey, blue

Type

Part Number

D4/8.SNNT2.I.ADO 1SNA399779R2400

Pkg

Weightpce(1 pce) g

50

13.00

1SNC163019S0201 - Rev. A

1

Color

D4/8.SF.I.ADO IDC Terminal Blocks
For 5 x 20 and 5 x 25 fuses - with test socket ADO - screw clamp 8 mm 0.315 in Spacing
1.5 mm²

Description–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not delivered with the terminal blocks),–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163110F0014

Ordering Details
Description

Color

Type

Part Number

pce

Fuse

With 2 test sockets
DIA 2 mm 0.079 inGrey

D4/8.SFT2.I.ADO

Main Technical Data
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

68.2 2.68"

55.9 2.20"

48.4 1.90"

94 3.70"

86.5 3.40"

180°

1SNA399777R1200

50

Weight(1 pce) g
13.00

Mounting Instructions

2

Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
6.3 A / 1.5 mm²
180 A
630 V
8000 V
IP20
NEMA 1Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.inIEC
D4/8.SF.I.ADO

Pkg

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

25.5 1.00"

RoHS

Gost R

8 mm 0.315 in Spacing

Accessories
Description
2

1
2
3
4
5

3

4

5

6

6

7

8

7
8
9

9

10 mm
0.394 in
5.2 mm0.205 inEnd Sections
1.5 mm
0.059 in
Lateral Jumper Bars 10 poles
35 A
Test Plugs
DIA 2 mm 0.079 in
Fuses
0.5 A
1A
2A
5A
Assembly Rods
2 poles
3 poles
4 poles
Spring Retaining Rings
Tools
Semi automatic tool
Hand tool
Terminal Block Markers Blank card
End Stops

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC Terminal Blocks
Description
Disconnect

Color
Profile aligned with D4/8.SF.I.ADO

Grey, Blue

TypePart Number

D4/8.SNNT2.I.ADO 1SNA399779R2400

Pkg

Weightpce(1 pce) g

50

13.00

Technical data valid for copper conductors only.

PAGE 35

1SNC163020S0201 - Rev. A

1

Color

D4/8.SF.I.ADO IDC Terminal Blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator and test socket ADO - screw clamp - 8 mm 0.315 in spacing
1.5 mm²

1SNC163110F0014

16 AWG

Description–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not delivered with the terminal blocks),–– Quickly identify the defective circuit thanks to blown fuse indicators,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering Details
Description

Color

Fuse

D4/8.SF.I.ADO

With blown fuse indicatorby LED 24 V AC/DC and2 test sockets
DIA 2 mm 0.079 inWith blown fuse indicator byneon 110 - 230 V AC and2 test sockets
DIA 2 mm 0.079 in

55.9 2.20"

48.4 1.90"

ADO
94 3.70"

Grey

D4/8.SFDT2.I.ADO

1SNA399782R0000

50

Grey

D4/8.SFLT2.I.ADO

1SNA399856R0200

50

13.00

Mounting Instructions
Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
6.3 A / 1.5 mm²
180 A
500 V
6000 V
IP20
NEMA 1Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC

180°

86.5 3.40"

Pkg

Weight(1 pce) g
13.00

Main Technical Data

68.2 2.68"

8 mm 0.315 in spacing

Part Numberpce2

25.5 1.00"

Type

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

Leakage current: 24 V < 4.5 mA; 110 V < 0.5 mA; 230 V < 0.7 mA

Accessories
Description
2

3

4

5

6

1
2
3
4
5

6

7

8

7
8
9

9

10 mm
0.394 in
5.2 mm0.205 inEnd Sections
1.5 mm
0.059 in
Lateral Jumper Bars 10 poles
35 A
Test Plugs
DIA 2 mm 0.079 in
Fuses
0.5 A
1A
2A
3.15 A
5A
Assembly Rods
2 poles
3 poles
4 poles
Spring Retaining Rings
Tools
Semi automatic tool
Hand tool
Terminal Block Markers Blank card
End Stops

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC Terminal Blocks
Description
Disconnect

Color
Profile aligned with D4/8.SF.I.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey, Blue

TypePart Number

D4/8.SNNT2.I.ADO 1SNA399779R2400

Pkg

Weightpce(1 pce) g

50

13.00

1SNC163021S0201 - Rev. B

1

Color

D4/8.SF.I.ADO IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket ADO - screw clamp 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not delivered with the terminal blocks),–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163139F0014

Ordering details
Description

TypePart Number

Fuse

With 2 test sockets
DIA 2 mm 0.079 in,With black marking for wire size
1-2.5 mm² (16-14 AWG)

Grey

ADO

55.9 2.20"

48.4 1.90"

86.5 3.40"

25.5 1.00"

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

180°

Weight(1 pce) g
13.00

D4/8.SFT2.I.ADO2

1SNA399762R1300

50

2

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
6.3 A / 2.5 mm²
300 A
630 V
8000 V
IP20
NEMA 1Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC68.2 2.68"

Pkg
pce

Main technical data

D4/8.SF.I.ADO

94 3.70"

Color

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

8 mm 0.315 in spacing

Gost R

Accessories
Description
2

3

4

5

6

7

8

1

End stops

23
4
5

End sections
Lateral jumper bars
Test plugs
Fuses

6

Assembly rods

7
8

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

9910 mm 0.394 in
5.2 mm 0.205 in
1.5 mm 0.059 in
10 poles 35 A
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC terminal blocks
Description
Disconnect

Color
Profile aligned with D4/8.SF.I.ADO

Grey, blue

Type

Part Number

D4/8.SNNT2.I.ADO2 1SNA399766R1700

Pkg

Weightpce(1 pce) g

50

13.00

Technical data valid for copper conductors only.

PAGE 37

1SNC163022S0201 - Rev. A

1

Color

D4/8.SF.I.ADO IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket ADO - screw clamp 8 mm 0.315 in spacing
2.5 mm²

1SNC163123F0014

14 AWG

Description–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not delivered with the terminal blocks),–– Quickly identify the defective circuit thanks to blown fuse indicators,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

TypePart Number

D4/8.SF.I.ADO

68.2 2.68"
180°

Grey

D4/8.SFLT2.I.ADO2

1SNA399768R2100

50

Weight(1 pce) g
13.00

With blown fuse indicator byneon 110 - 230 V AC and 2 test
sockets DIA 2 mm 0.079 in,with black marking for wire size
1-2.5 mm² (16-14 AWG)
With blown fuse indicator by
LED 24 V AC/DC and 2 test
sockets DIA 2 mm 0.079 in,with black marking for wire
size 1-2.5 mm² (16-14 AWG)

Grey

D4/8.SFDT2.I.ADO2

1SNA399770R2700

50

13.00

55.9 2.20"

48.4 1.90"

94 3.70"

86.5 3.40"

Main technical data

8 mm 0.315 in spacing

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
6.3 A / 2.5 mm²
300 A
500 V
6000 V
IP20
NEMA 1Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

25.5 1.00"

Pkg
pce

Fuse

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

Leakage current: 24 V < 4.5 mA; 110 V < 0.5 mA; 230 V < 0.7 mA

Accessories
1

3

2

4

5

6

7

8

9

Description

Color

1

End stops

23
4
5

End sections
Lateral jumper bars
Test plugs
Fuses

6

Assembly rods

7
8

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card9

10 mm 0.394 in
5.2 mm 0.205 in
1.5 mm 0.059 in
10 poles 35 A
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC terminal blocks
Description
Disconnect

Color
Profile aligned with D4/8.SF.I.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey, blue

Type

Part Number

D4/8.SNNT2.I.ADO2 1SNA399766R1700

Pkg

Weightpce(1 pce) g

50

13.00

1SNC163023S0201 - Rev. B

2

Color

D4/8.SN.I.ADO IDC terminal blocks
Disconnect with lever - with test socket - ADO screw clamp 8 mm 0.315 in spacing
1.5 mm²

1SNC163120F0014

16 AWG

Description–– Disconnect terminal blocks aligned with fuse holder terminal blocks,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

pce

Disconnect

With 2 test sockets
DIA 2 mm 0.079 inGrey, blue

D4/8.SNNT2.I.ADO

Main technical data
D4/8.SN.I.ADO

Rigid: Solid/Stranded
Flexible without ferrule55.9 2.20"

48.4 1.90"

94 3.70"

86.5 3.40"

25.5 1.00"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

180°

1SNA399779R2400

50

Weight(1 pce) g
13.00

Mounting instructions

2

Rail

TH 35-7.5,
TH 35-15

0.34-1.5 mm²
0.34-1.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
10 A / 1.5 mm²
180 A
630 V
8000 V
IP20
NEMA 1Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

IEC68.2 2.68"

Pkg

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
Gost R

8 mm 0.315 in spacing

Accessories
Description
2

3

4

5

6

1
2
3
4
5
6
7
8

7

8

10 mm
0.394 in
5.2 mm0.205 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A
Test plugs
DIA 2 mm 0.079 in
Assembly rods
2 poles
3 poles
4 poles
Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey
Black

White

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
TGA8
ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00
1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Fuse IDC terminal blocks
Description
Fuse

Color
Profile aligned with D4/8.SN.I.ADO

Type
Grey

D4/8.SFT2.I.ADO

Part Number
1SNA399777R1200

Pkg

Weightpce(1 pce) g

50

13.00

Technical data valid for copper conductors only.

PAGE 39

1SNC163100S0201 - Rev. A

1

Color

D4/8.SN.I.ADO IDC terminal blocks
Disconnect with lever - with test socket - ADO screw clamp 8 mm 0.315 in spacing
2.5 mm²

1SNC163124F0014

14 AWG–– Disconnect terminal blocks aligned with fuse holder terminal blocks,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

Disconnect

With 2 test sockets
DIA 2 mm 0.079 in,with black marking forwire size 1-2.5 mm²(16-14 AWG)

Grey, blue

D4/8.SNNT2.I.ADO2

Main technical data
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

55.9 2.20"
25.5 1.00"

8 mm 0.315 in spacing

48.4 1.90"

94 3.70"180°

1SNA399766R1700

50

Weight(1 pce) g
13.00

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²
1-2.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

A4
6.3 A / 2.5 mm²
300 A
630 V
8000 V
IP20
NEMA 1Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC68.2 2.68"

Pkg
pce

D4/8.SN.I.ADO

86.5 3.40"

UL

CSA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

Accessories
Description
1

2

3

4

5

6

1

End stops

23
4
5

End sections
Lateral jumper bars
Test plugs
Assembly rods

6
7

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

8
7

8

Color
10 mm 0.394 in
5.2 mm 0.205 in
1.5 mm 0.059 in
10 poles 35 A
DIA 2 mm 0.079 in
2 poles
3 poles
4 poles

Dark grey
Grey
Black

White

Type
BAM4
BAZ1
FEDAD10
PC81-10
FC2
TGA8
ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399758R2700
1SNA173523R1100
1SNA007865R2600
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
100
10
10
10
10
1
1
1

14.00
5.30
3.00
5.00
1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Fuse IDC terminal blocks
Description
Fuse

Color
Profile aligned with D4/8.SN.I.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Type
Grey

Part Number

D4/8.SFT2.I.ADO2 1SNA399762R1300

Pkg

Weightpce(1 pce) g

50

13.00

1SNC163025S0201 - Rev. A

2

Description

D1/5.ADO IDC terminal blocks
Feed-through ADO - ADO - 5 mm 0.197 in spacing
1 mm²
18 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC163001F0014

Feed-throughFeed-through

Grey
Blue
OrangeD1/5.ADO
D1/5.N.ADO
D1/5.ADO

1SNA199563R2400
1SNA199565R2600
1SNA199564R2500

Main technical data

Mounting instructions
IEC

ADO
D1/5.ADO

Rigid: Solid/Stranded
Flexible without ferruleUL

0.2-1 mm²0.22-1 mm²Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

Rail

22-18 AWG

Wire stripping
length

56 2.20"48.5 1.91"

TH 35-7.5,
TH 35-15

2

Tool

Screw clamp

45.5 1.79"

50
50
50

Weight(1 pce) g
5.00
5.00
5.00

13.5 A / 1 mm²
120 A1000 V
8000 V
IP20
NEMA 17 A / 18 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

24 0.95"

5 mm 0.197 in spacing

Accessories
Description
2

1
2
3

3

4

5

6

4
5
6
7

7

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
24 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

White

Type
BAM4
BAZ1
FEMAD3
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
SCAD5
CBM5
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA199551R2000
1SNA178745R1400
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
50
1
1
1

14.00
5.30
2.50
3.30
5.00
6.70
8.40
16.90
0.30
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D1/5.ADO

Green-yellow

TypeD1/5.P.ADO

Part Number
1SNA399031R2200

Pkg

Weightpce(1 pce) g

50

9.00

Technical data valid for copper conductors only.

PAGE 41

1SNC163039S0201 - Rev. A

1

Color

D1.5/6.ADO IDC terminal blocks
Feed-through ADO - ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163063F0014

pce

Feed-through1SNA199051R2600
1SNA199053R2000
1SNA199052R2700

Main technical data
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

0.34-1.5 mm²
0.34-1.5 mm²

22-14 AWG

22-16 AWG

Wire stripping
length

56 2.20"48.5 1.91"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

45.5 1.79"

50
50
50

Mounting instructions

2

D1.5/6.ADO

D1.5/6.ADO
D1.5/6.N.ADO
D1.5/6.ADO

Grey
Blue
OrangeWeight(1 pce) g
6.00
6.00
6.00

17.5 A / 1.5 mm² 10 A / 14 AWG 18 A / 16 AWG
180 A
1000 V
600 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

USR

US

cCSAusGost R

24 0.95"

6 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCross spacing
5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 injumpers
Universal screw jumper bar kit N°I
Universal screw jumper bar kit N°III
Circuit separators 0 mm
0 in
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

White

Type
BAM4
BAZ1
FEMAD3
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
EL6
BJDP1
BJDP3
SCAD
CBM5
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA173627R2100
1SNA179623R0300
1SNA179625R0500
1SNA196896R0000
1SNA178745R1400
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
50
1
1
1

14.00
5.30
2.50
4.40
6.70
8.90
11.20
22.40
0.10
7.00
5.00
205.00
29.00
7.50

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D1.5/6.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeD1.5/6.P.ADO

Part Number
1SNA199098R2600

Pkg

Weightpce(1 pce) g

50

6.00

1SNC163040S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

D2.5/8.ADO IDC terminal blocks
Feed-through ADO - ADO - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163034F0014

pce

Feed-throughD2.5/8.ADO
D2.5/8.N.ADO
D2.5/8.ADO

Grey
Blue
Orange1SNA199059R0600
1SNA199061R2000
1SNA199060R0300

Main technical data
ADO

D2.5/8.ADO

With black marking forwire size 1-2.5 mm²(16-14 AWG)

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

1-2.5 mm²
1-2.5 mm²

16-14 AWG

16-14 AWG

Wire stripping
length

56 2.20"48.5 1.91"

TH 35-7.5,
TH 35-15

2

Tool

Screw clamp

45.5 1.79"

50
50
50

Weight(1 pce) g
9.00
9.00
9.00

24 A / 2.5 mm² 15 A / 14 AWG 25 A / 14 AWG
300 A
1000 V
600 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

USR

US

cCSAusGost R

24 0.95"

8 mm 0.315 in spacing

Accessories
Description
2

1
2
3

3

4

5

6

4
5
6

7

7

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
41 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
Cross spacing
5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 injumpers
Universal screw jumper bar kit N°I
Universal screw jumper bar kit N°III
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

White

Type
BAM4
BAZ1
FEMAD3
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
SCAD
EL6
BJDP1
BJDP3
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA196896R0000
1SNA173627R2100
1SNA179623R0300
1SNA179625R0500
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
2.50
4.50
6.00
10.00
12.22
20.00
0.10
7.00
5.00
205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D2.5/8.ADO

Green-Yellow

TypeD2.5/8.P.ADO

Part Number
1SNA199091R1700

Pkg

Weightpce(1 pce) g

50

9.00

Technical data valid for copper conductors only.

PAGE 43

1SNC163041S0201 - Rev. A

1

Color

D4/8.ADO IDC terminal blocks
Feed-through ADO-ADO - 8 mm 0.315 in spacing
4 mm²
12 AWG

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.).

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC163075F0014

Feed-through2

With white
marking for wire
size 4 mm² (12 AWG)

D4/8.ADO
D4/8.N.ADO
D4/8.ADO

Grey
Blue
Orange

1SNA399244R1400
1SNA399318R1600
1SNA399801R0400

Main technical data

Mounting instructions
IEC

ADO

Rigid: Solid/Stranded
Flexible without ferrule

UL

4 mm²
4 mm²

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

Rail

14-12 AWG

Wire stripping
length

56 2.20"48.5 1.91"

45.5 1.79"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

D4/8.ADO

5050
50

Weight(1 pce) g
9.00
9.00
9.00

32 A / 4 mm²
480 A
1000 V
8000 V
IP20

25 A / 12 AWG
600 V

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

24 0.95"

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

4
5
6

7

7

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 inJumper bars
2 poles
41 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
Cross spacing
5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 injumpers
Universal screw jumper bar kit N°I
Universal screw jumper bar kit N°III
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey

Grey

White

Type
BAM4
BAZ1
FEMAD3
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
SCAD
EL6
BJDP1
BJDP3
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA196896R0000
1SNA173627R2100
1SNA179623R0300
1SNA179625R0500
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
2.50
4.50
6.00
10.00
12.22
20.00
0.10
7.00
5.00
205.00
29.00
8.20

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with D4/8.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-Yellow

Type
D4/8.P.ADO

Part Number
1SNA399250R2600

Pkg

Weightpce(1 pce) g

50

9.00

1SNC163042S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

D1/5.P.ADO IDC terminal blocks
Ground ADO-ADO - 5 mm 0.197 in spacing
1 mm²
18 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Up to 2 wires per connection.

1SNC163098F0014

Ordering details
Description

Color

Type

Part Number

pce

GroundScrewless rail connection Green-yellow

D1/5.P.ADO

1SNA399031R2200

Main technical data
ADO

D1/5.P.ADO

Rigid: Solid/Stranded
Flexible without ferruleUL

0.2-1 mm²0.22-1 mm²Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
1 mm²
Rated short-time withstand current (1s) 120 A
Protection
IP20

CSA

Rail

22-18 AWG

Wire stripping
length

56 2.20"

TH 35-7.5,
TH 35-15

2

Tool

Screw clamp

48.5 1.91"

50

Weight(1 pce) g
9.00

Mounting instructions
IEC

50 1.97"

Pkg

18 AWG
TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

25 0.984"

5 mm 0.197 in spacing

Accessories
Description
1

2

1
2
3

4

4

Dark grey
Grey

White

Type
BAM4
BAZ1
FEMAD3
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163048S0201 - Rev. A

3

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 45

D1.5/6.P.ADO IDC terminal blocks
Ground ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Up to 2 wires per connection.

Ordering details
1SNC163032F0014

Description

Color

Type

Part Number

GroundScrewless rail connection Green-yellow

D1.5/6.P.ADO

1SNA199098R2600

Main technical data
ADO

D1.5/6.P.ADO

Rigid: Solid/Stranded
Flexible without ferrule

IEC

UL

CSA

Rail

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
lengthRigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
1.5 mm²
Rated short-time withstand current (1s) 180 A
ProtectionIP20

48.5 1.91"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

50 1.97"50

Weight(1 pce) g
6.00

Mounting instructions

2

56 2.20"Pkg
pce

16 AWG

16 AWG
TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

USR

US

cCSAusGost R

25 0.984"

6 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

3

4

4

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color
Dark grey
Grey

White

Type
BAM4
BAZ1
FEMAD3
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
7.50

1SNC163049S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/8.P.ADO IDC terminal blocks
Ground ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Up to 2 wires per connection.

1SNC163088F0014

Ordering details
Description

Color

Type

Part Number

pce

GroundScrewless rail connection Green-yellow
with black marking forwire size 1-2.5 mm²(16-14 AWG)

D2.5/8.P.ADO

1SNA199091R1700

Main technical data
D2.5/8.P.ADO

ADO

Rigid: Solid/Stranded
Flexible without ferrule

56 2.20"48.5 1.91"

50

Weight(1 pce) g
9.00

2

Mounting instructions
IEC

UL

1-2.5 mm²
1-2.5 mm²

16-14 AWG

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
2.5 mm²
Rated short-time withstand current (1s) 300 A
Protection
IP20

CSA

Rail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

50 1.97"Pkg

14 AWG
TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
25 0.984"
RoHS

USR

Gost R

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

4

4

Dark grey
Grey

White

Type
BAM4
BAZ1
FEMAD3
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163050S0201 - Rev. A

3

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 47

D4/8.P.ADO IDC terminal blocks
Ground ADO-ADO - 8 mm 0.315 in spacing
4 mm²
12 AWG

Description–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator dependent,–– Secure mounting or removal from the rail,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,

Ordering details
1SNC163097F0014

Description

Color

Type

Part Number

GroundScrewless rail connection, Green-yellow
with white marking forwire size 4 mm²(12 AWG)

D4/8.P.ADO

1SNA399250R2600

Main technical data

2

ADO

Rigid: Solid/Stranded
Flexible without ferrule

UL

4 mm²
4 mm²

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
4 mm²
Rated short-time withstand current (1s) 480 A
Protection
IP20

CSA

Rail

14-12 AWG

Wire stripping
length

56 2.20"48.5 1.91"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

50 1.97"50

Weight(1 pce) g
9.00

Mounting instructions
IEC

D4/8.P.ADO

Pkg
pce

12 AWG
TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

25 0.984"

US

cCSAusGost R

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

4

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color
Dark grey
Grey

White

Type
BAM4
BAZ1
FEMAD3
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
2.50
205.0029.00
8.20

1SNC163051S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD1.5/6.D2.ADO IDC terminal blocks
Double deck with 2 feed-through circuits ADO-ADO 6 mm 0.236 in spacing
1.5 mm²

Description–– Save space with 2 decks terminal block,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163040F0014

Description

Color

Type

Part Number

pceFeed-throughWith 2 feed-throughcircuits

Grey

D1.5/6.D2.ADO

1SNA199480R2600

Main technical data
ADO

D1.5/6.D2.ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

0.28-1.5 mm²
0.34-1.5 mm²

83 3.27"

Rail

TH 35-7.5,
TH 35-15

2

Wire stripping
lengthTool

Screw clamp

75.5 2.97"50

Weight(1 pce) g
18.00

Mounting instructions
IEC

93 3.66"Pkg

17.5 A / 1.5 mm²
180 A
800 V
6000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

52.5 2.07"

6 mm 0.236 in spacing

Accessories
Description
1

3

2

1
2
3

4

5

6

7

8

4
5
6
7
8

10 mm
0.394 in
5 mm
0.197 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
Shield connectors
Inner deck jumper bars Inner deck jumper bars
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

Grey

White

Type
BAZH1
FED2AD2
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
SCAD
CBD2S
ITVE
OUPAD
OUMAD
RC610

Part Number
1SNK900102R0000
1SNA199476R2500
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA196896R0000
1SNA178408R1400
1SNA179694R0300
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
50
20
1
1
1

24.00
7.00
4.40
6.70
8.90
11.20
22.40
1.40
205.0029.00
7.50

1SNC163043S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 49

D1/5.SNT2.ADO IDC terminal blocks
Disconnect with blade - with test socket ADO-ADO - 5 mm 0.197 in spacing
Description

1 mm²–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

1SNC163042F0014

Ordering details
Description

Color

Type

Disconnect

With 2 test sockets
DIA 2 mm 0.079 inGrey

D1/5.SNT2.ADO

1SNA399231R0700

Main technical data

2

ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

52 2.05"

59.5 2.34"

72 2.83"

64.5 2.54"

50

Weight(1 pce) g
9.00

Mounting instructions
UL

CSA

0.2-1 mm²0.22-1 mm²

Rail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

68.5 2.70"

Pkg
pce

IEC
D1/5.SNT2.ADO

Part Number

10 A / 1 mm²
120 A
320 V
4000 V
IP20

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
37 1.46"

RoHS

Gost R

5 mm 0.197 in spacing

Accessories
Description
1

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5
6

Test plugs
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

4

6

Color

7

10 mm
0.394 in
5.2 mm0.205 in
2 mm
0.079 in
2 poles13.5 A
3 poles
10 polesDIA 2 mm 0.079 in

Dark grey
Grey
Orange

Black

White

Type
BAM4
BAZ1
FEDAD5BJADO5-2
BJADO5-3
BJADO5-10
FC2
CDB2
OUPAD
OUMAD
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199354R0200
1SNA205955R0300
1SNA205956R0400
1SNA205963R0300
1SNA007865R2600
1SNA179635R0700
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
100
50
1
1
1

14.00
5.30
2.70
1.00
1.00
5.00
205.0029.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163052S0201 - Rev. A

7

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD1.5/6.SNT2.ADO IDC terminal blocks
Disconnect with blade - with test socket ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

1SNC163042F0014

Ordering details
Description

TypePart Number

Disconnect

With 2 test sockets
DIA 2 mm 0.079 inGrey

D1.5/6.SNT2.ADO

Main technical data

52 2.05"

59.5 2.34"

72 2.83"

64.5 2.54"

1SNA199144R2000

50

Weight(1 pce) g
9.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

0.34-1.5 mm²
0.34-1.5 mm²

22-14 AWG

22-16 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15

2

Tool

Screw clamp

68.5 2.70"

Pkg
pce

ADO

D1.5/6.SNT2.ADO

Color

10 A / 1.5 mm² 8 A / 14 AWG
180 A
500 V
600 V
6000 V
IP20
NEMA 1

15 A / 16 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

37 1.46"

RoHS

USR

US

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5
6

Test plugs
Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

4

6

Color

7

10 mm
0.394 in
5.2 mm0.205 in
2 mm
0.079 in
2 poles17.5 A
3 poles
10 polesDIA 2 mm 0.079 in

Dark grey
Grey
Orange

Black

White

Type
BAM4
BAZ1
FEDAD5BJADO6-2
BJADO6-3
BJADO6-10
FC2
CDB2
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199354R0200
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA007865R2600
1SNA179635R0700
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
100
50
1
1
1

14.00
5.30
2.70
1.00
1.00
6.00
205.00
29.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163053S0201 - Rev. A

7

Technical data valid for copper conductors only.

PAGE 51

D2.5/8.SNT2.ADO IDC terminal blocks
Disconnect with blade - with test socket ADO-ADO 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– Ease your disconnect operations with the disconnect knife blade operated by hand,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

1SNC163091F0014

Ordering details

2

Description

TypePart Number

Disconnect

ADO

With 2 test sockets
DIA 2 mm 0.079 inWith black marking forwire size 1-2.5 mm²(16-14 AWG)

Grey

D2.5/8.SNT2.ADO

37 1.46"

52 2.05"

1SNA199231R2700

50

Weight(1 pce) g
12.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

1-2.5 mm²
1-2.5 mm²

16-14 AWG

16-14 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15

Tool

Screw clamp

59.5 2.34"

64.5 2.54"

68.5 2.70"

Pkg
pce

Main technical data

D2.5/8.SNT2.ADO

72 2.83"

Color

15 A / 2.5 mm² 15 A / 14 AWG 15 A / 14 AWG
300 A
500 V
600 V
600 V
6000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

8 mm 0.315 in spacing

USR

US

cCSAusGost R

Accessories
Description
1

3

2

4

1
2
3
4
5

Dark grey
Grey
Black

White

Type
BAM4
BAZ1
FEDAD5
FC2
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199354R0200
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
100
1
1
1

14.00
5.30
2.70
205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163054S0201 - Rev. A

5

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2 mm
0.079 in
Test plugs
DIA 2 mm 0.079 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD1.5/8.SF.ADO IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket ADO-ADO - 8 mm 0.315 in spacing
1.5 mm²

1SNC163092F0014

16 AWG

Description–– The TE Connectivity ADO System® fuse holders provide circuit protection for control applications,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description

TypePart Number

Fuse

ADO

With 2 test sockets
DIA 2 mm 0.079 in or
DIA 2.3 mm 0.091 inGrey

D1.5/8.SFT.ADO

1SNA199208R1100

56 2.20"
43 1.69"50

Weight(1 pce) g
13.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length2

TH 35-7.5,
TH 35-15

Tool

Screw clamp

49 1.93"90.5 3.56"

80.5 3.17"

Pkg
pce

Main technical data

D1.5/8.SF.ADO

98 3.86"

Color

6.3 A / 1.5 mm² 8 A / 16 AWG
180 A
630 V
600 V
8000 V
IP20
NEMA 1

10 A / 16 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

C

RoHS

USR

US

cCSAusGost R

Accessories
Description
1

2

1

End stops
End sections
Test plugs
Fuses

Color
10 mm
0.394 in
5.2 mm0.205 in
1.5 mm
0.059 in
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

3

4

2
3
4

5

6

5

Assembly rods

7

8

6
7

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

8

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD7
FC2.MC
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199382R2700
1SNA107239R0300
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
20
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.80
1.00

1.00

205.0029.00
8.20

1SNC163056S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 53

D1.5/8.SF.ADO IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator and test socket ADO-ADO - 8 mm 0.315 in spacing
1.5 mm²

1SNC163092F0014

16 AWG

D1.5/8.SF.ADO

Ordering details
Description

Color

Type

Part Number

Grey

D1.5/8.SFLT.ADO

1SNA199211R2300

50

Weight(1 pce) g
14.00

Fuse

With blown fuse indicator by neon
110 - 230 V AC and 2 test sockets
With blown fuse indicator by
LED 24 V AC/DC and 2 test sockets

Grey

D1.5/8.SFDT.ADO

1SNA199212R2400

50

14.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

0.34-1.5 mm²
0.34-1.5 mm²

22-16 AWG

22-16 AWG

Wire stripping
length

49 1.93"

56 2.20"8 mm 0.315 in spacing

TH 35-7.5,
TH 35-15

Tool

Screw clamp

43 1.69"

Pkg
pce

ADO

80.5 3.17"

98 3.86"–– The TE Connectivity ADO System® fuse holders provide circuit protection for control applications,–– Quickly identify the defective circuit thanks to blown fuse indicators,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Main technical data

90.5 3.56"

6.3 A / 1.5 mm² 8 A / 16 AWG
180 A
500 V
600 V
6000 V
IP20
NEMA 1

10 A / 16 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

USR

US

cCSAusGost R

Leakage current: 24 V : < 4.5 mA / 110 V : < 0.5 mA / 230 V : < 0.7 mA

Accessories
Description
1

2

1

End stops
End sections
Test plugs
Fuses

Color
10 mm
0.394 in
5.2 mm0.205 in
1.5 mm
0.059 in
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

3

4

2
3
4

5

6

5

Assembly rods

7

8

6
7

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

8

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD7
FC2.MC
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199382R2700
1SNA107239R0300
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
20
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.80
1.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163057S0201 - Rev. B

2

Description

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/8.SF.ADO2 IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²

1SNC163086F0014

14 AWG

D2.5/8.SF.ADO2

Description–– The TE Connectivity ADO System® fuse holders provide circuit protection for control applications,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

pce

Fuse

With 2 test sockets DIA 2 mm
0.079 in or DIA 2.3 mm 0.091 inand black marking for wire size
1-2.5 mm² (16-14 AWG)

Grey

D2.5/8.SFT.ADO2

Main technical data
ADO

80.5 3.17"

56 2.20"

49 1.93"

98 3.86"90.5 3.56"

1SNA199184R1100

50

Weight(1 pce) g
14.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

1-2.5 mm²
1-2.5 mm²

16-14 AWG

16-14 AWG

Wire stripping
length2

TH 35-7.5,
TH 35-15

Tool

Screw clamp

43 1.69"Pkg

6.3 A / 2.5 mm² 10 A / 14 AWG 10 A / 14 AWG
300 A
630 V
600 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing
C

RoHS

USR

US

cCSAusGost R

Accessories
Description
2

1

End stops
End sections
Test plugs
Fuses

10 mm
0.394 in
5.2 mm0.205 in
1.5 mm
0.059 in
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

3

4

2
3
4

5

6

5

Assembly rods

7

8

6
7

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

8

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD7
FC2.MC
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199382R2700
1SNA107239R0300
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
20
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.80
1.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC terminal blocks
Description
Disconnect

Color
Profile aligned with D2.5/8.SF.ADO

Grey, blue

Type

Part Number

D2.5/8.SNNT.ADO2 1SNA199186R1300

Pkg

Weightpce(1 pce) g

50

18.00

Technical data valid for copper conductors only.

PAGE 55

1SNC163058S0201 - Rev. A

1

Color

D2.5/8.SF.ADO2 IDC terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator and test socket ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²

1SNC163045F0014

14 AWG–– The TE Connectivity ADO System® fuse holders provide circuit protection for control applications,–– Quickly identify the defective circuit thanks to blown fuse indicators,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description
Fuse

80.5 3.17"

TypePart Number

With blown fuse indicator byneon 110 - 230 V AC and 2 test
sockets and black marking
for wire size 1-2.5 mm² (1614 AWG)
With blown fuse indicator by
LED 24 V AC/DC and 2 test
sockets and black marking
for wire size 1-2.5 mm² (1614 AWG)

Grey

D2.5/8.SFLT.ADO2

1SNA199187R1400

50

Grey

D2.5/8.SFDT.ADO2

1SNA199188R2500

50

15.00

56 2.20"

ADO

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

Rail

1-2.5 mm²
1-2.5 mm²

16-14 AWG

16-14 AWG

Wire stripping
length8 mm 0.315 in spacing

TH 35-7.5,
TH 35-15

Tool

Screw clamp

43 1.69"

Pkg

Weight(1 pce) g
15.00

Main technical data
49 1.93"

98 3.86"

Color

pce

D2.5/8.SF.ADO2

90.5 3.56"

6.3 A / 2.5 mm² 10 A / 14 AWG 10 A / 14 AWG
300 A
500 V
600 V
600 V
6000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

USR

US

cCSAusGost R

Leakage current: 24 V : < 4.5 mA / 110 V : < 0.5 mA / 230 V : < 0.7 mA

1

3

5

7

2

4

Accessories
Description

Color

1

End stops

2
3
4

End sections
Test plugs
Fuses

5

Assembly rods

6
7

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

6

8

8

10 mm
0.394 in
5.2 mm0.205 in
1.5 mm
0.059 in
DIA 2 mm 0.079 in
0.5 A
1A
2A
3.15 A
5A
2 poles
3 poles
4 poles

Dark grey
Grey
Black

Type
BAM4
BAZ1
FEDAD7
FC2.MC
FU520

TGA8

White

ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199382R2700
1SNA107239R0300
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA008289R1600
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
20
10
10
10
10
10
10
10
10
10
1
1
1

14.00
5.30
3.80
1.00

1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Disconnect IDC terminal blocks
Description
Disconnect

Color
Profile aligned with D2.5/8.SF.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey, blue

Type

Part Number

D2.5/8.SNNT.ADO2 1SNA199186R1300

Pkg

Weightpce(1 pce) g

50

18.00

1SNC163059S0201 - Rev. B

2

Description

D2.5/8.SNNT.ADO2 IDC terminal blocks
Disconnect - with test socket ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²

1SNC163085F0014

14 AWG

Description–– Disconnect terminal blocks aligned with fuse holder terminal blocks,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

pce

Disconnect

D2.5/8.SNNT.ADO2

With 2 test sockets
DIA 2 mm 0.079 in andblack marking for wire
size 1-2.5 mm²(16-14 AWG)

Grey, blue

D2.5/8.SNNT.ADO2

Main technical data
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

8 mm 0.315 in spacing

49 1.93"

56 2.20"
43 1.69"

1SNA199186R1300

50

Weight(1 pce) g
18.00

2

Mounting instructions
IEC

UL

CSA

1-2.5 mm²
1-2.5 mm²

16-14 AWGRail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

90.5 3.56"

98 3.86"80.5 3.17"

Pkg

10 A / 2.5 mm² 10 A / 14 AWG
300 A
630 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

Gost R

Accessories
Description
1

3

5

2

4

6

Color

1

End stops

2
3
4

End sections
Test plugs
Assembly rods

5
6

Spring retaining rings
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

7

10 mm
0.394 in
5.2 mm0.205 in
1.5 mm
0.059 in
DIA 2 mm 0.079 in
2 poles
3 poles
4 poles

Dark grey
Grey
Black

White

Type
BAM4
BAZ1
FEDAD7
FC2.MC
TGA8
ANT
OUPAD
OUMAD
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199382R2700
1SNA107239R0300
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
20
20
10
10
10
10
1
1
1

14.00
5.30
3.80
1.00
1.00

205.0029.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Fuse IDC terminal blocks
Description
Fuse

Color
Profile aligned with D2.5/8.SNNT.ADO

Grey

Type

Part Number

D2.5/8.SFT.ADO2 1SNA199184R1100

Pkg

Weightpce(1 pce) g

50

14.00

Technical data valid for copper conductors only.

PAGE 57

1SNC163061S0201 - Rev. A

7

1SNC162115S0201

3

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Spring loaded screw clamp technology
Technologies presentation		

60

Overview			

62

Feed-through		
4 mm² / 12 AWG

M4/6.RS		

63

6 mm² / 12 AWG

M6/8.RS		

64

10 mm² / 6 AWG

M10/10.RS		

65

Disconnect with blade		
4 mm² / 10 AWG

M4/6.SNTS		

66

Disconnect with push-turn knob		
6 mm² / 12 AWG

M6/8.STP.RS

With test

67

Disconnect with screwdriver sliding link		
D6/8.ST.RS		
D6/8.ST1.RS.IP20

With insulated test sockets

3

68
69

1SNC162115S0201

6 mm² / 12 AWG

PAGE 59

Dedicated applications terminal blocks
Spring loaded screw clamp technology

The safest screw connection!

TE connectivity screw clamp springloaded technology offers additional
contact safety thanks to the
combination of a spring under clamp
preventing screw loosening and the useof special hook type ferrules providing
pull-out proof termination.

3

Approved by numerous national electricity providers in
EU,Africa and Asia since many years.
Comply with IEC and BS TS5018 standards.

RoHS

ISO 9001

The ultimate protection against unwanted opened circuits
Safety first!
Connection of up to two hook type ferrules onto screw
clamp & conducting bar provide "pull-out proof" cable terminations.
44

Circuit continuity ensured
Reinforcement spring beneath the clamp maintains permanent contact pressure even if screw clamp is loose ensuring long term security of cable connections and electricalcircuits.

1

2

Robust designed
Springs firmly positioned in deep recesses and cannot beeasily removed or ejected.

4

4
3
4

1 Hook type ferrule locked in clamp

3 Deep recesses spring position

2

4 Multiple reinforcements

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Permanent contact pressure

1SNC161122S0201

Multiple plastic "ribs" compensate spring pressure andavoid bending effect on body leading to a robust terminal
block body construction.

TE connectivity spring loaded screw clamp technology
The safety connection for demanding working conditions
Exclusive design provide robustness and connection
safetyThe TE connectivity screw clamp spring loaded terminal isdesigned to guaranty electrical continuity even when screw
are loosened unintentionally.
It features all the benefits of our screw clamp with additional
vibration,shock resistant and maintenance free performances.

High density wiring
The screw clamp spring loaded terminal can fit up to two conductors equipped with bent ferrules per clamp.

Features

The TE connectivity exclusiveanti-release system creates acontrolled locking-screw effectthanks to the 2 overlapping tabs
that maintain the clamp parts. The
screw is locked in total safety. The
retightening campaigns are notneeded anymore!

The clamp is punched, which
increases the number of screw
threads by 30 % meaning ahigh torque resistance

Screw

3

Screw clamp
Conductive
linking bar
Stripped wire

Hook type ferrule
Provide pull-out
proof connection

Hardened steel makes theconnection very reliable

SpringPowerfull steel spring underneath
Clamp ensures pemanent contactpressure

The screw tightens the
conductive bar to the cable.
There is no torsion effectapplied to the cable

Flap avoiding the insertion of cable
underneath the clamp

Hook type ferrule

From 0.22 mm² up to 10 mm²

1SNC161123S0201

From 24 AWG up to 6 AWG

PAGE 61

Dedicated applications terminal blocks
Spring loaded screw clamp technology

Feed-throughDisconnect with blade

Section

1/4

IEC

UL/CSA4 mm²12 AWG

6 mm²
10 mm²

Disconnect withscrewdriver sliding link

12 AWG
6 AWG

M4/6.RS

M4/6.SNTS

6 mm 0.236 in

6 mm 0.236 in

M6/8.RS

M6/8.STP.RS

D6/8.ST.RS

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

M10/10.RS
10 mm 0.394 in

1SNC160059S0201

3

Disconnect withpush-turn knob

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.RS spring loaded screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing
4 mm²

Description–– Mainly dedicated to energy applications based on BS TS5018 standard,–– Security: specific shape in linking bar to lock the hook type ferrule, spring clamp can maintain contact pressure even if screw clamp is loose.

Ordering details
Description

Color

1SNC161086F0014

Feed-through

Grey
Blue

Part Number

M4/6.RS
M4/6.N.RS

1SNA115930R1300
1SNA125930R1500

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

M4/6.RS

63.5 2.50"

50 1.97"

Pkg

Weightpce(1 pce) g

50
50

11.00
11.00

Mounting instructions
IEC

1 conductor
per clamp

BS
TS 5018CSA

0.2-4 mm²0.22-4 mm²
0.28-1.65 mm²
A3
32 A / 4 mm²
480 A
1000 V
8000 V
IP20

RailWire stripping
length
Tool

25 A
500 V

TorqueNEMA 1

G32, TH 35-7.5,
TH 35-15
13 mm
0.51 inFlat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 Nm
4.4 - 7.1 lb.in

3

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

56 2.20"

61 2.40"

Type

Each screw clamp holds up to 2 hook type ferrules as shown (not supplied)
22.5 0.87"
27.5 1.08"

6 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

4

5

6

7

4
5
6
7

Dark grey
Grey

Black
White

Type
BAM4
BAZ1
FEMR8
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
BJDP4
AL2
FC2
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116987R0200
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA174781R2500
1SNA163043R2100
1SNA007865R2600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
100
1

14.00
5.30
3.00
4.40
6.70
8.90
11.20
22.40
5.00
0.90
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Note: Use of jumper bars or cross spacing jumpers requires the user to cut the partition.

1SNC161056S0201 - Rev. B

3

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCross spacing jumpers Universal screw jumper bar kit N°IV
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 63

M6/8.RS spring loaded screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
6 mm²
12 AWG

Description–– Mainly dedicated to energy applications based on BS TS5018 standard,–– Security: specific shape in linking bar to lock the hook type ferrule, spring clamp can maintain contact pressure even if screw clamp is loose.

Ordering details
Description

Color

1SNC161083F0014

Feed-through

Type
Grey

Part Number

M6/8.RS

1SNA115685R1200

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

50 1.97"

BS
TS 5018

0.5-10 mm²
0.5-6 mm²

1 conductor
per clamp

M6/8.RS

Weight(1 pce) g

50

17.00

Mounting instructions
IEC

3

Pkg
pce

CSA

Rail

20-12 AWG

Wire stripping
length

0.28-2.5 mm²
A541 A / 6 mm²
720 A
800 V
8000 V
IP20

25 A

25 A / 12 AWG

500 V

600 V

Tool
TorqueNEMA 1

G32, TH 35-7.5,
TH 35-15
13 mm
0.51 inFlat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in
0.8 - 1 Nm
7.1 - 8.9 lb.in

63.5 2.50"

C

CE

RoHS

US

cCSAusGost R

56 2.20"

61 2.40"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

Each screw clamp holds up to 2 hook type ferrules as shown (not supplied)

22.5 0.87"
27.5 1.08"

8 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

Dark grey
Grey

White
White

Type
BAM4
BAZ1
FEMR8
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
AL4-M3-R1
FC4
BP8.A4
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116987R0200
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA206722R0200
1SNA167860R0100
1SNA173888R2000
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
50
10
10
1

14.00
5.30
3.00
4.50
6.00
10.00
12.22
20.00
1.62
10.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Note: Use of jumper bars requires the user to cut the partition.

1SNC161152S0201 - Rev. B

7

4
5
6
7

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inJumper bars
2 poles
41 A
3 poles
4 poles
5 poles
10 polesTest sockets
DIA 4 mm 0.157 in
Test plugs
DIA 4 mm 0.157 in
Short circuit plugs DIA 4 mm 0.157 in
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM10/10.RS spring loaded screw clamp terminal blocks
Feed-through - 10 mm 0.394 in spacing
10 mm²
6 AWG

Description–– Mainly dedicated to energy applications based on BS TS5018 standard,–– Security: specific shape in linking bar to lock the hook type ferrule, spring clamp can maintain contact pressure even if screw clamp is loose.

Ordering details

1SNC161090F0014

Description

Color

Feed-throughGrey

66.5 2.51"

BS
TS 5018

0.5-16 mm²
0.5-10 mm²
0.28-6 mm²
A541 A / 10 mm² 40 A
1200 A
800 V
500 V
8000 V
IP20
NEMA 1

1SNA115320R2700

Weight(1 pce) g

25

30.00

CSA

Rail

20-6 AWG

Wire stripping
length65 A / 6 AWG
600 V

Tool
TorqueG32, TH 35-7.5,
TH 35-15
14 mm
0.55 inFlat screwdriverØ 5.5 - 6 mm
Ø 0.217 - 0.236 in
1.2 - 1.4 Nm
10.6 - 12.3 lb.in

3

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

CE

RoHS

US

cCSAus59 2.32"

64 2.52"

M10/10.RS

Pkg
pce

Mounting instructions
IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

54 2.12"

Part Number

Main technical data
1 conductor
per clamp

M10/10.RS

Type

Gost R

Each screw clamp holds up to 2 hook type ferrules as shown (not supplied)

23.5 0.93"

4.6

13.3
17

28.5 1.12"

10 mm 0.394 in spacing

Accessories
Description
2

3

4

5

6

7

8

1

End stops

10 mm
5.2 mm
2.5 mm2 poles
3 poles
4 poles
5 poles
10 poles20 poles

0.394 in
0.205 in
0.098 in
57 A

2
3

End sections
Jumper bars (1)

4
5
6
7
8

Posts (1)
Screws (1)Test sockets
DIA 4 mm 0.157 in
Test plugs
DIA 4 mm 0.157 in
Terminal block markers Blank card

Dark grey
Grey

White
White

Type
BAM4
BAZ1
FEMR10
BJS10

BJS10-20
PT101
VSJ11
AL4-M4
FC4
RC1010Part Number
1SNK900001R0000
1SNK900002R0000
1SNA114434R0500
1SNA164585R1700
1SNA164586R1000
1SNA164587R1100
1SNA168273R1100
1SNA164588R2200
1SNA177654R0000
1SNA163181R1100
1SNA163394R2600
1SNA206723R0300
1SNA167860R0100
1SNA238000R1600

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
50
50
10
1

14.00
5.30
3.30
17.00
17.00
17.00
17.00
17.00
17.00
1.00
0.60
1.30
10.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Note: Use of jumper bars requires the user to cut the partition.
(1) Complete jumper : jumper bar + post x number of poles + screw x number of poles.

1SNC161141S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

PAGE 65

M4/6.SNTS spring loaded screw clamp terminal blocks
Disconnect with blade - with test socket - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Mainly dedicated to energy markets for security purposes on CT circuits,–– Security: specific shape in linking bar to lock the ferrule, spring clamp can maintain contact pressure evenif screw clamp is loose.

Ordering details
Description
1SNC161152F0014

Disconnect

Color
With test socket DIA 2 mm 0.079 in

Type
Grey

Part Number

M4/6.SNTS

1SNA115229R2000

Main technical data
Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
53 2.09"
55.5
2.23"

68.5 2.69"

RailG32, TH 35-7.5,
TH 35-15

22-10 AWG

24-10 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

10 A / 4 mm²
480 A
500 V

10 A / 10 AWG 15 A / 10 AWG

IP20NEMA 1

300 V

600 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

48
1.89"

66 2.59"

11.00

CSA

3

61 2.40"

50

UL

M4/6.SNTS

44.5 1.75"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

CE

RoHS

USR

US

cCSAusGost R

18 0.71"
23 0.91"

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

4

6

1

Color

2
3
4
5

10 mm
5.2 mmEnd sections
2.8 mmJumper bars
1 poles
Lateral jumper bars 10 poles
Circuit separators 3 mm

6
7
8

Test plugs
DIA 2 mm 0.079 in
Shield connectors
Terminal block markers Blank card

End stops

0.394 in
0.205 in
0.110 in
24 A
35 A
0.118 in

Dark grey
Grey
Grey
Grey
Black
White

Type
BAM4
BAZ1
FEM6
AD2.5
PC61-10
SCFM6
SCF6
FC2
CBM5
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA114205R2000
1SNA163311R2200
1SNA114825R0500
1SNA118707R0300
1SNA007865R2600
1SNA178745R1400
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
50
10
20
20
100
50
1

14.00
5.30
2.40
1.60
5.00
4.00

7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

8

1SNC161138S0201 - Rev. A

7

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM6/8.STP.RS spring loaded screw clamp terminal blocks
Disconnect with push-turn knob - with test socket- 8 mm 0.315 in spacing
6 mm²

1/4

12 AWG

Description–– Mainly dedicated to energy markets for security purposes on CT circuits,–– Security: specific shape in linking bar to lock the ferrule, spring clamp can maintain contact pressure evenif screw clamp is loose.

Ordering details

1SNC161234F0014

Description
Disconnect

Color
With 2 test sockets
DIA 4 mm 0.157 in

83.5 3.29"

Grey, yellow

M6/8.STP.RS

IEC

BSTS 5018

1SNA115678R0200

Pkg

Weightpce(1 pce) g

25

29.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.5-10 mm²
0.5-6 mm²

CSA

Rail

20-12 AWG

Wire stripping
length

0.28-2.5 mm²
A524 A / 6 mm²
720 A
500 V
6000 V

25 A

25 A / 12 AWG

500 V

600 V

Tool
TorqueNEMA

G32, TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in
0.8 - 1 Nm
7.1 - 8.9 lb.in

3

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

CE

RoHS

US

cCSAusGost R

76 2.99"

81 3.19"72.5 2.85"

Part Number

Main technical data
1 conductor
per clamp

M6/8.STP.RS

Type

Each screw clamp holds up to 2 hook type ferrules as shown (not supplied)
33.7 1.33"
38.5 1.52"

8 mm 0.315 in spacing

Accessories
Description
1

3

2

4

1
2
3
4
5

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inJumper bars
1 poles
24 A
Test plugs
DIA 4 mm 0.157 in
Short circuit plugs DIA 4 mm 0.157 in

6

With test DIA 4 mm 0.16 in
Terminal block markers Blank card

End stops

Color

Type

Dark grey
Grey
Grey
White
Red

6

White

1SNK900001R0000
1SNK900002R0000
1SNA116991R0600
1SNA114205R2000
1SNA167860R0100
1SNA173888R2000
1SNA196789R2400
1SNA196792R1700
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
10
50
10
10
20
20
1

14.00
5.30
4.70
1.60
10.00
10.00
14.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161151S0201 - Rev. A

5

Beige

BAM4
BAZ1
FEMR8T
AD2.5
FC4
BP8.A4
BNSTP2
BNSTP1
RC810

Part Number

Technical data valid for copper conductors only.

PAGE 67

D6/8.ST.RS spring loaded screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Mainly dedicated to energy markets for security purposes on CT circuits,–– Security: specific shape in linking bar to lock the ferrule, spring clamp can maintain contact pressure even ifscrew clamp is loose.

Ordering details
1SNC161277F0014

Description

Color

DisconnectGrey85.6 3.37"

D6/8.ST.RS

1SNA115914R0700

Pkg

Weightpce(1 pce) g

32

28.00

Mounting instructions
IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

3Part Number

Main technical data
1 conductor
per clamp

D6/8.ST.RS

Type

BS
TS 5018CSA

0.5-10 mm²
0.5-6 mm²0.28-2.5 mm²
A524 A / 6 mm²
720 A
400 V
6000 V

Rail
Wire stripping
lengthTool
TorqueNEMA

G32, TH 35-7.5,
TH 35-15
16 mm
0.51 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
0.8 - 1 Nm
7.1 - 8.9 lb.in

78.4 3.08"

55.8 2.19"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

Each screw clamp holds up to 2 hook type ferrules as shown (not supplied)

45 1.77"

8 mm 0.315 in spacing

Description
1

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5

Fastening kits
Test sockets

4

6

Color
End stops 0.394 in
0.205 in
1 mm
0.039 in
2 poles
41 A
3 poles
4 poles
20 polesSub assembly post + screw + washer
DIA 4 mm 0.157 in IP20

Type

Dark grey
Grey

Yellow
Black
Green
Grey
Blue

7

Red

8
6
7
8

DIA 4 mm 0.157 in
Test plugs
DIA 4 mm 0.157 in IP20
Short circuit
2 polesbridges
3 poles
4 poles
Terminal block markers Blank card

Red
Yellow

White

BAM4
BAZ1
FEM8T6
BJS8
BJS8-20
EV6I
AJS9
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
AL4-M3
FC4-1
SC-JB8-2
SC-JB8-3
SC-JB8-4
RC810Part Number
1SNK900001R0000
1SNK900002R0000
1SNA215266R0100
1SNA164581R1300
1SNA164582R1400
1SNA164583R1500
1SNA174789R0500
1SNA206394R0200
1SNA179726R0200
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206721R0100
1SNA167927R1000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA234000R0200

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
5
20
25
25
25
25
25
25
50
10
25
25
25
1

14.00
5.30
4.40
3.10
3.10
3.10
3.20
2.00
3.60
3.60
3.60
3.60
3.60
3.60
1.10
11.00
2.00
3.40
4.70
8.20

1SNC161153S0201_dupli - Rev. A

Accessories

D6/8.ST.RS spring loaded screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Mainly dedicated to energy markets for security purposes on CT circuits,–– Security: specific shape in linking bar to lock the ferrule, spring clamp can maintain contact pressure evenif screw clamp is loose.

Ordering details

1SNC161233F0014

Description
Disconnect

Color
With 2 yellow test sockets
DIA 4 mm 0.157 in

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section

15.1
0.59"
78.4 3.08"

D6/8.ST1.RS.IP20

1SNA115831R0400

BS
TS 5018

CSA

Weight(1 pce) g

32

38.00

0.28-2.5 mm²

RailG32, TH 35-7.5,
TH 35-15

Wire stripping
lengthScrew clamp

16 mm
0.51 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
0.8 - 1 Nm
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

A5

Tool

24 A / 6 mm²

TorqueRated short-time withstand current (1s)

720 A

Rated voltage

400 V

Impulse withstand voltage

6000 V

Disconnect device
Tool
TorqueNEMA

Protection

3

Test socket
Tool
Torque45 1.77"

Pkg
pce

Mounting instructions
IEC

D6/8.ST.RS

55.8 2.19"

Grey

Part Number

Main technical data
1 conductor
per clamp

85.6 3.37"

TypeØ 3.5 mm
Ø 0.138 in
0.6 N.m
5.34 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

8 mm 0.315 in spacing

RoHS

Gost R

Each screw clamp holds up to 2 hook type ferrules as shown (not supplied)

Description
1

3

2

1

End stops

4

2
3
4

End sections
Jumper bars
Test sockets

Color
10 mm
0.394 in
5.2 mm0.205 in
1 mm
0.039 in
1 poles
24 A
DIA 4 mm 0.157 in IP20

Dark grey
Grey
Grey
Black
Green
Grey
Blue

5

7

6

Red

5
6

7

DIA 4 mm 0.157 in IP20
2 poles
3 poles
4 poles
Terminal block markers Blank card
Test plugs
Short circuitbridgesRed
Yellow

White

Type
BAM4
BAZ1
FEM8T6
AD2.5
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
FC4-1
SC-JB8-2
SC-JB8-3
SC-JB8-4
RC810Part Number
1SNK900001R0000
1SNK900002R0000
1SNA215266R0100
1SNA114205R2000
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA167927R1000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
10
50
25
25
25
25
25
10
25
25
25
1

14.00
5.30
4.40
1.60
3.60
3.60
3.60
3.60
3.60
11.00
2.00
3.40
4.70
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 69

1SNC161095S0201_dupli - Rev. A

Accessories

1SNC165030S0201

4

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Stud technology
Technologies presentation			

72

Overview				

73

D… series
Two studs		
Feed-through		
35 mm² / 1 AWG 		

D35/27.FF		

74

70 mm² / 000 AWG 		

D70/32.FF 		75

120 mm² / 300 Kcmil 		

D120/42.FF 		

76

185 mm² / 500 Kcmil 		

D185/55.FF

77

300 mm² / 1000 Kcmil 		D300/55.FF

78

One stud - One screw clamp		
Feed-through		
35 mm² / 1 AWG 		

D35/27.AF 		

79

70 mm² / 000 AWG 		

D70/32.AF 		

80

120 mm² / 300 AWG 		

D120/42.AF

81

185 mm² / 500 AWG 		

D185/55.AF

82

D… series mounting instructions			

83

4

M… series
Two studs		
Feed-through25 mm² / 2 AWG		

M35/26.FF		

50 mm² / 00 AWG		

M70/31.FF		

84
85

70 mm² / 000 AWG-250 Kcmil

M120/35.FF		

86

120 mm² / 500 Kcmil		M300/42.FF		87

One stud - One screw clamp		
Feed-through		
25 mm² / 2 AWG		

M35/26.AF		

50 mm² / 0 AWG		

M70/31.AF		

8889

70 mm² / 000 AWG-250 Kcmil

M120/35.AF

90

120 mm² / 500 Kcmil		M300/42.AF

91

One stud		Feed-through		
25 mm² / 2 AWG		

M35/26.F		

92

50 mm² / 00 AWG		

M70/31.F		

93

M120/35.F		

94

120 mm² / 500 Kcmil		M300/42.F		95

M… series mounting instructions			

96

1SNC165030S0201

70 mm² / 000 AWG-250 Kcmil

PAGE 71

TE Connectivity Stud technology
The connection for power and energy circuits
Reliability first
Stud technology is designed to ensure a reliable connection
thanks to the combination of:– – Vibration resistant equipements (nuts, washers),– – Lugs crimped on the cable provide pull-out proof
termination.

This technology is very popular on the American market andparticularely in the energy applications.

Available configurations

4

Two studs

One screw clamp / one stud

One stud

Connection technics

M4-M5
6 mm 28 AWG

M635 mm 21 AWG

M8
70 mm 2000 AWG

M10
120 mm 2
300 Kcmil

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

M12
185 mm 2
500 Kcmil

M16
300 mm 2
1000 Kcmil

1SNC165028S0201

Up to 300 mm² / 1000 Kcmil

Dedicated applications terminal blocks
Stud technology

Two studs

Feed-throughFeed-throughSectionSectionIEC

UL/CSA

35 mm²70 mm²120 mm²
185 mm²
300 mm²

1 AWG
000 AWG
300 Kcmil
500 Kcmil
1000 Kcmil

D35/27.FF
D70/32.FF
D120/42.FF
D185/55.FF
D300/55.FF

27 mm 1.063 in
32 mm 1.260 in
42 mm 1.654 in
55 mm 2.165 in
55 mm 2.165 inIEC

UL/CSA

25 mm²50 mm²70 mm²120 mm²

2/4 AWG
00/0 AWG
250 Kcmil/000 AWG
500 Kcmil

M35/26.FF
M70/31.FF
M120/35.FF
M300/42.FF

26 mm 1.024 in
31 mm 1.220 in
35 mm 1.380 in
42 mm 1.653 in

4

One stud - One Screw-clamp

Feed-throughFeed-throughSectionSectionIEC

UL/CSA

35 mm²70 mm²120 mm²
185 mm²

1 AWG
000 AWG
300 Kcmil
500 Kcmil

D35/27.AF
D70/32.AF
D120/42.AF
D185/55.AF

27 mm 1.063 in

32 mm 1.260 in
42 mm 1.654 in
55 mm 2.165 inIEC

UL/CSA

25 mm²50 mm²70 mm²120 mm²

2/4 AWG
0 AWG
250 Kcmil/000 AWG
500 Kcmil

M35/26.AF
M70/31.AF
M120/35.AF
M300/42.AF

26 mm 1.024 in
31 mm 1.220 in
35 mm 1.380 in
42 mm 1.653 in

One studFeed-throughIEC

UL/CSA

25 mm²50 mm²70 mm²120 mm²

2/4 AWG
00/0 AWG
250 Kcmil/000 AWG
500 Kcmil

M35/26.F
M70/31.F
M120/35.F
M300/42.F

1SNC165029S0201

Section
26 mm 1.024 in
31 mm 1.220 in
35 mm 1.380 in
42 mm 1.653 in

PAGE 73

D35/27.FF power terminal blocks
Feed-through - 27 mm 1.062 in spacing
Description

35 mm²–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

1 AWG

Ordering details
1SNC165010F0014

Description

Color

Feed-through2 studs M6 without coverD35/27.FF

Grey

1SNA190001R2000

Main technical data

113 4.45"
52 2.05"

DIN

UL
2.5-35 mm² 2.5-50 mm² 1 AWG

CSA

Lugs
Tool

2.5-35 mm² 2.5-35 mm²
C4

UL

Rail

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

TorqueJumper screw
Tool

59 2.32"=

66.5 2.62"

Pkg

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

10

Weight(1 pce) g
130.00

Mounting instructions
NF C

IEC
Screw clamp=

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D35/27.FF

Type

IEC

UL

CSA

125 A
35 mm²1000 V
8000 V

125 A
1 AWG
600 V

TorqueTH 35-7.5,
TH 35-15
Wrench
H10 mm
3 - 6 N.m
26.1 - 52 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
Torque56.5 2.22"

Wire stripping
length27 mm 1.062 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

6

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS27-2
BJS27-3
DRF6
CPUF35RC810

1SNK900102R0000
1SNA205772R1300
1SNA205773R1400
1SNA205767R1600
1SNA190016R1600
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
34.00
52.00
4.00
8.30
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165006S0201 - Rev. C

5Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD70/32.FF power terminal blocks
Feed-through - 32 mm 1.260 in spacing
Description

70 mm²000 AWG–– Rated cross section up to 300 mm2 / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130 and
DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M8 without coverD70/32.FF

Grey

56 2.20"

67 2.64"74.5 2.93"=

70 2.76"

Pkg

DIN

6-95 mm²
6-70 mm²C66-70 mm²
6-70 mm²

UL
000 AWG

CSA

Rail
Lugs
Tool

UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

3

Weight(1 pce) g
269.00

Mounting instructions
NF C

IEC

=

1SNA190002R2100

Main technical data

Screw clamp

140 5.51"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D70/32.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

192 A
70 mm²1000 V
8000 V

170 A
000 AWG
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH13 mm
6 - 12 N.m
52 - 104 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
TorqueWire stripping
length32 mm 1.260 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

6

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS32-2
BJS32-3
DRF8
CPUF70RC810

1SNK900102R0000
1SNA205774R1500
1SNA205775R1600
1SNA205768R2700
1SNA190017R1700
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
66.00
105.80
5.00
12.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165005S0201 - Rev. C

5Technical data valid for copper conductors only.

PAGE 75

D120/42.FF power terminal blocks
Feed-through - 42 mm 1.653 in spacing
120 mm²
300 Kcmil

Description–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130 and
DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M10 without
cover

76 2.99"

84 3.31"=70 2.76"

1SNA190003R2200

Main technical data

Screw clamp

64 2.51"=

D120/42.FF

Grey

Pkg

DIN

UL
6-150 mm² 6-120 mm² 300 Kcmil

CSA

Rail
Lugs
Tool

6-120 mm²
C8

UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
423.00

Mounting instructions
NF C

IEC

140 5.51"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D120/42.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

269 A
120 mm²
1000 V
8000 V

269 A
300 Kcmil
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH17 mm10 - 20 N.m
87 - 174 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
Torque42 mm 1.653 in spacing

Wire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

6

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS42-2
BJS42-3
DRF10
CPUF120RC810

1SNK900102R0000
1SNA205776R1700
1SNA205777R1000
1SNA205769R2000
1SNA190018R2000
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
93.00
153.00
7.00
24.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165004S0201 - Rev. C

5Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD185/55.FF power terminal blocks
Feed-through - 55 mm 2.165 in spacing
185 mm²
500 Kcmil

Description–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M12 without
cover

90 3.54"97.5 3.84"=

81.5 3.21"

1SNA190004R2300

Main technical data

Screw clamp

71 2.79"=

D185/55.FF

Grey

Pkg

DIN

UL
25-240 mm² 6-185 mm² 500 Kcmil

CSA

Rail
Lugs
Tool

6-185 mm²
C11

UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
615.00

Mounting instructions
NF C

IEC

163 6.42"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D185/55.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

353 A
185 mm²
1000 V
8000 V

353 A
500 Kcmil
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH24 mm14 - 30 N.m
123.9 - 265.5 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
TorqueWire stripping
length55 mm 2.165 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

6

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS551-2
BJS551-3
DRF12
CPUF185
RC810

1SNK900102R0000
1SNA205778R2100
1SNA205779R2200
1SNA205770R2500
1SNA190019R2100
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
158.00266.00
8.00
40.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165010S0201 - Rev. C

5Technical data valid for copper conductors only.

PAGE 77

D300/55.FF power terminal blocks
Feed-through - 55 mm 2.165 in spacing
300 mm²
1000 Kcmil

Description–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M16 without
cover

99 3.89"106.5 4.20"=

81.5 3.21"

1SNA190005R2400

Main technical data

Screw clamp

72 2.83"=

D300/55.FF

Grey

Pkg

DIN

UL
CSA
25-300 mm² 6-300 mm² 1000 Kcmil

Rail6-300 mm²

Lugs
Tool
UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
775.00

Mounting instructions
NF C

IEC

163 6.42"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D300/55.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

520 A
300 mm²
1000 V
8000 V

460 A
1000 Kcmil
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH24 mm25 - 50 N.m
217 - 435 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
TorqueWire stripping
length55 mm 2.165 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

6

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS551-2
BJS551-3
DRF16
CPUF185
RC810

1SNK900102R0000
1SNA205778R2100
1SNA205779R2200
1SNA205771R1200
1SNA190019R2100
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
158.00266.00
7.00
40.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165011S0201 - Rev. C

5Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD35/27.AF power terminal blocks
Feed-through - 27 mm 1.062 in spacing
Description

35 mm²–– Rated cross section up to 240 mm² / 500 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130 and
DIN 46234, various marking options, rail or base mounting.

1 AWG

Ordering details
1SNC165019F0014

Description

Color

Feed-through1 stud M6 + 1 screw clamp
with covers

90 3.54"82.5 3.24"

78.2 3.07"
70.7 2.78"
56.5 2.22"

D35/27.AF

Grey

1SNA190006R2500

Main technical data

Screw clamp

136.5 5.37"

Part Numbers

Pkg
qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D35/27.AF

Type

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

10

Weight(1 pce) g
149.00

Mounting instructions
NFC

DIN

UL
2.5-35 mm² 2.5-50 mm² 1 AWG

CSA

Lugs
Tool

2.5-35 mm² 2.5-35 mm²C4IEC
2.5-35 mm²
2.5-35 mm²UL
1-12 AWG

IEC

UL

125 A
35 mm²1000 V
8000 V

130 A
1 AWG
600 V

Rail

CSA

TorqueJumper screw
Tool

CSA

TorqueScrew clamp
Tool
Torque27 mm 1.062 in spacing

Wire stripping
lengthTH 35-7.5,
TH 35-15
Wrench
H10 mm
3 - 6 N.m
26.1 - 52 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in
Allen key
5 mm
0.197 in
3.5 ± 0.5 N.m
30.9 ± 4.43 lb.in
28 mm
1.102 in4

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Numbers

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS27-2
BJS27-3
DRF6
CPUF35RC810

1SNK900102R0000
1SNA205772R1300
1SNA205773R1400
1SNA205767R1600
1SNA190016R1600
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
34.00
52.00
4.00
8.30
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165003S0201 - Rev. B

5

Technical data valid for copper conductors only.

PAGE 79

D70/32.AF power terminal blocks
Feed-through - 32 mm 1.260 in spacing
Description

70 mm²000 AWG–– Rated cross section up to 240 mm² / 500 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130 and
DIN 46234, various marking options, rail or base mounting.

Ordering details
1SNC165019F0014

Description

Color

Feed-through1 stud M8 + 1 screw clamp
with covers

70 2.75"

113.2 4.45"
105.7 4.16"

95.8 3.77"
88.3 3.47"

4

D70/32.AF

Grey

1SNA190007R2600

Main technical data

Screw clamp

165 6.49"

Part Numbers

Pkg
qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D70/32.AF

Type

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

3

Weight(1 pce) g
269.00

Mounting instructions
NFC

DIN

6-95 mm²
6-70 mm²

6-70 mm²
6-70 mm²

UL
000 AWG

CSA

Rail
Lugs
Tool

IEC
6-95 mm²
6-70 mm²

UL
CSA
10-000 AWG

IEC

UL

192 A
70 mm²1000 V
8000 V

165 A
000 AWG
600 V

TorqueJumper screw
Tool

CSA

TorqueScrew clamp
Tool
Torque32 mm 1.260 in spacing

Wire stripping
lengthTH 35-7.5,
TH 35-15
WrenchH13 mm
6 - 12 N.m
52 - 104 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in
Wrench
6 mm
0.236 in
7 ±1 N.m
61.9 ± 8.85 lb.in
33 mm
1.299 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Numbers

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS32-2
BJS32-3
DRF8
CPUF70RC810

1SNK900102R0000
1SNA205774R1500
1SNA205775R1600
1SNA205768R2700
1SNA190017R1700
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
66.00
105.80
5.00
12.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165007S0201 - Rev. B

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD120/42.AF power terminal blocks
Feed-through - 42 mm 1.653 in spacing
Description

120 mm²–– Rated cross section up to 240 mm² / 500 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

300 Kcmil

Ordering details
1SNC165019F0014

Description

Color

Feed-through1 stud M10 + 1 screw clamp
with covers

137.2 5.40"
129.7 5.10"

115 4.52"
107.5 4.23"
70 2.75"

D120/42.AF

Grey

1SNA190008R0700

Main technical data

Screw clamp

197 7.75"

Part Numbers

Pkg
qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D120/42.AF

Type

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
423.00

Mounting instructions
NFC

DIN

UL
6-150 mm² 6-120 mm² 300 Kcmil

CSA

Rail
Lugs
Tool

6-120 mm²C8IEC6-150 mm²6-120 mm²

UL
CSA
10 AWG-300 Kcmil

IEC

UL

269 A
120 mm²
1000 V
8000 V

240 A
300 Kcmil
600 V

TorqueJumper screw
Tool

CSA

TorqueScrew clamp
Tool
TorqueWire stripping
length42 mm 1.653 in spacing

TH 35-7.5,
TH 35-15
WrenchH17 mm10 - 20 N.m
87 - 174 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in
Allen key
8 mm
0.315 in
11 ± 1 N.m
97.36 ± 8.85 lb.in
38 mm
1.496 in4

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Numbers

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS42-2
BJS42-3
DRF10
CPUF120RC810

1SNK900102R0000
1SNA205776R1700
1SNA205777R1000
1SNA205769R2000
1SNA190018R2000
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
93.00
153.00
7.00
24.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165008S0201 - Rev. B

5

Technical data valid for copper conductors only.

PAGE 81

D185/55.AF power terminal blocks
Feed-through - 55 mm 2.165 in spacing
Description

185 mm²–– Rated cross section up to 240 mm² / 500 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

500 Kcmil

Ordering details
1SNC165019F0014

Description

Color

Feed-through1 stud M12 + 1 screw clamp
with covers

81.5 3.20"

159.5 6.28"
152 5.98"

136 5.35"
125.5 5.06"

4

D185/55.AF

Grey

1SNA190009R0000

Main technical data

Screw clamp

228.5 9.00"

Part Numbers

Pkg
qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D185/55.AF

Type

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
937.00

Mounting instructions
NFC

DIN

UL
25-240 mm² 6-185 mm² 500 Kcmil

CSA

Rail
Lugs
Tool

6-185 mm²
C11IEC
25-240 mm²
25-185 mm²

UL
CSA
4 AWG-500 Kcmil

IEC

UL

353 A
185 mm²
1000 V
8000 V

320 A
500 Kcmil
600 V

TorqueJumper screw
Tool

CSA

TorqueScrew clamp
Tool
TorqueWire stripping
length55 mm 2.165 in spacing

TH 35-7.5,
TH 35-15
WrenchH24 mm14 - 30 N.m
123.9 - 265.5 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
53.1 - 106.2 lb.in
Allen key
10 mm
0.394 in
15 ± 1 N.m
132.7 ± 8.85 lb.in
47 mm
1.850 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Numbers

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS551-2
BJS551-3
DRF12
CPUF185
RC810

1SNK900102R0000
1SNA205778R2100
1SNA205779R2200
1SNA205770R2500
1SNA190019R2100
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
158.00266.00
8.00
40.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165009S0201 - Rev. B

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSPower terminal blocks
Mounting instructions
Main dimensions mm

4

Type

Mounting with:

A

B

C

D

F

G1

G2

H

7.5
7.5
7.5
13.5
13.5

6.5
6.5
6.5
6.5
6.5

/
/
/
8.5
8.5

63.5
72.5
83.5
103.5
105

136.5
165
197
228.5
/

160
190.5
255.5
295
295

82.5
105.7
129.7
151.5
/

Dimensions mm

2 Screws
2 Screws
2 Screws
4 Screws
4 Screws

100.5
120
120
135
135

Marking

2 RC 810 or
1 RC 1010

Locking foot operatingwith screwdriver DIA. 4 mm
RPC type setting
marker or RC 810
marker2 slots, 2 RC810 not
separated or
1 RC 1010 in 1 slot

Center opening (to be made after jumper
bar has been removed) "monostable action".

Locking
Between blocks with pins

As soon as the screwdriver is removed, the locking
foot comes back to closed position

Side opening with
2 positions.
The locking foot remains
in open or closed position.

Jumper bar

With M3 screw

M3 nut on one side
M3 nut + washer on the other side–– Move the marker holders up–– Cut out the partition–– Screw the jumper bar

Mounting of the derivative system

Unlocking

1SNC165014S0201

D35/27...
D70/32...
D120/42...
D185/55...
D300/55...

Locking

PAGE 83

M35/26.FF stud terminal blocks
Feed-through - 26 mm 1.024 in spacing
Description

25 mm²–– Compact two stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

2 AWG

1SNC165008F0014

Ordering details
Description

Color

Type

Part Number

Feed-through2 studs M6 linked
by 1 removablebar 16 x 4 mm

M35/26.FF

Grey

1SNA115140R2300

Main technical data
M35/26.FF

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

59 2.33"

56.5 2.23"
33.5 1.32"

51.5 2.03"

4

DIN

UL
2.5-50 mm² 10-2 AWG

4-35 mm²4-25 mm²C3

2.5-25 mm²

DIN

UL

G32, TH 35-7.5,
TH 35-15
Wrench
H10 mm

CSA

4.5-9 N.m
39.8-79.6 lb.in

TorqueJumper screw
Tool

IEC
DIN
UL
16 x 4 mm 0.63 x 0.16 in
101 A
125 A
115 A
25 mm²35 mm²2 AWG
1000 V
600 V
8000 VBar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

CSA
Rail
max 4 AWG
Lugs
Tool

CSA

Torque

125 A
4 AWG
600 V

Screw clamp
Tool

38.5 1.52"

26 mm 1.024 in spacing

10

Weight(1 pce) g
64.00

Mounting instructions
NFC

IEC

66 2.60"
18.5 0.73"

Pkg
pce

TorqueWire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP26
CPP261
CPP262
CPP263PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113689R2400
1SNA168202R1300
1SNA168201R1200
1SNA163403R2000
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
6.40
5.00
10.00
17.00
0.46
7.50

1SNC165019S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM70/31.FF stud terminal blocks
Feed-through - 31 mm 1.220 in spacing
Description

50 mm²–– Compact two stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

00 AWG

Ordering details
1SNC165006F0014

Description

Color

Type

Part Number

Feed-through2 studs M8 linked
by 1 removablebar 20 x 5 mm

M70/31.FF

Grey

1SNA115143R1200

Main technical data
Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

NFC

DIN

6-70 mm²6-50 mm²C5

2.5-50 mm²

IEC
66 2.60"
66 2.60"
58.5 2.30"

63.5 2.50"

22 0.87"10

Weight(1 pce) g
110.00

Mounting instructions

Lugs
M70/31.FFUL
2.5-70 mm² 4-00 AWG

DIN

UL

G32, TH 35-7.5,
TH 35-15
WrenchH13 mm

CSA

6-12 N.m
53.1-106.2 lb.in

TorqueJumper screw
Tool

IEC
DIN
UL
20 x 5 mm 0.78 x 0.20 in
150 A
178 A
175 A
50 mm²50 mm²00 AWG
1000 V
600 V
8000 VBar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

CSA
Rail
max 0 AWG
Lugs
Tool

CSA

Torque

200 A
0 AWG
600 V

Screw clamp
Tool

34 1.34"

4

TorqueWire stripping
length

39 1.54"

31 mm 1.220 in spacing

Pkg
pce

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP31
CPP311
CPP312
CPP313PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113690R2100
1SNA168204R1500
1SNA168203R1400
1SNA163409R0600
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
6.70
7.00
14.00
23.00
0.46
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165020S0201 - Rev. B

3

Color

Technical data valid for copper conductors only.

PAGE 85

M120/35.FF stud terminal blocks
Feed-through - 35 mm 1.380 in spacing
Description

70 mm²250 Kcmil–– Compact two stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

1SNC165007F0014

Ordering details
Description

Color

Type

Part Number

Feed-through2 studs M8 linked
by 1 removablebar 25 x 5 mm

M120/35.FF

Grey

1SNA115146R1500

Main technical data
M120/35.FF

69 2.72"

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

66 2.60"
58.5 2.30"

63.5 2.50"
34 1.34"

NFC

DIN

6-95 mm²
6-70 mm²C6

2.5-70 mm²
2.5-70 mm²

IEC

DIN

CSA
Rail
max 000 AWG
Lugs
Tool

G32, TH 35-7.5,
TH 35-15
WrenchH13 mmUL

CSA

6-12 N.m
53.1-106.2 lb.in

TorqueJumper screw
Tool

IEC
DIN
25 x 5 mm 1 x 0.20 in
192 A
220 A
70 mm²70 mm²1000 V
8000 VBar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

UL
2-250 kcmil

UL

CSA

255 A
250 Kcmil
600 V

270 A
000 AWG
600 V

TorqueScrew clamp
Tool
Torque39 1.54"

35 mm 1.380 in spacing

10

Weight(1 pce) g
130.00

Mounting instructions

Lugs

27 1.06"

4

Pkg
pce

Wire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP35
CPP351
CPP352
CPP353PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113691R1600
1SNA168206R1700
1SNA168205R1600
1SNA163418R2600
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
10.00
8.00
20.00
20.00
0.46
7.50

1SNC165021S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM300/42.FF stud terminal blocks
Feed-through - 42 mm 1.653 in spacing
120 mm²
500 Kcmil

Description–– Compact two stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

1SNC165007F0014

Ordering details
Description

Color

Type

Part Number

Feed-through2 studs M10 linked
by 1 removablebar 32 x 8 mm

M300/42.FF

Grey

1SNA115149R2000

Main technical data
Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

46 1.81"

64 2.52"
56.5 2.22"

61.5 2.42"

35 1.38"

DIN

UL
CSA
0-500 kcmil max 500 Kcmil

50-150 mm² 6-150 mm²50-120 mm² 6-120 mm²
C8IEC
93 3.66"

DIN

UL

CSA

TorqueG32, TH 35-7.5,
TH 35-15
WrenchH16 mm
10-20 N.m
88.5-177 lb.in

Jumper screw
Tool
IEC
DIN
UL
32 x 8 mm 1.26 x 0.32 in
269 A
265 A
230 A
120 mm² 120 mm² 500 Kcmil
1000 V
600 V
8000 VBar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

Rail
Lugs
Tool

CSA
550 A
500 Kcmil
600 V

51 2.01"

42 mm 1.653 in spacing

10

Weight(1 pce) g
220.00

Mounting instructions
NFC

M300/42.FF

Pkg
pce

4

TorqueScrew clamp
Tool
TorqueWire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers

End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP42
CPP421
CPP422
CPP423PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113692R1700
1SNA168208R2100
1SNA168207R1000
1SNA163424R1400
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
20.00
13.00
30.00
40.00
0.46
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165022S0201 - Rev. B

3

Color

Technical data valid for copper conductors only.

PAGE 87

M35/26.AF stud terminal blocks
Feed-through - 26 mm 1.024 in spacing
25 mm²
2 AWG

Description–– Compact one stud / one clamp terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

Ordering details
1SNC165013F0014

Description

Color

Feed-through1 stud M6 + 1 screw clamp

71 2.80"

68.5 2.70"

63.5 2.50"

Pkg

1SNA115139R1600

10Weight(1 pce) g
60.00

Mounting instructions

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

18.5 0.73"

38.5 1.52"

M35/26.AF

Grey

Main technical data

66 2.60"

33.5 1.32"

Part Number

pce

M35/26.AF

4

Type

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

NFC

DIN

UL
2.5-50 mm² 10-2 AWG

4-35 mm²4-25 mm²C3

2.5-25 mm²

CSA
10-4 AWG

Rail
Lugs
Tool

IEC
DIN
UL
6-50 mm² 6-50 mm² 14-2 AWG
6-25 mm²CSA
10-4 AWG

IEC

DIN

UL

CSA

Torque

101 A
25 mm²1000 V
8000 V

115 A
25 mm²

115 A
2 AWG
600 V

125 A
4 AWG
600 V

Screw clamp
Tool

TorqueG32, TH 35-7.5,
TH 35-15
Wrench
H10 mm
4.5-9 N.m
39.8-79.6 lb.in

Jumper screw
Tool

TorqueWire stripping
length

Wrench
H10 mm
5 ± 0.5 N.m
44.25 ± 4.43 lb.in
19 mm
0.748 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

26 mm 1.024 in spacing

RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP26
CPP261
CPP262
CPP263PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113689R2400
1SNA168202R1300
1SNA168201R1200
1SNA163403R2000
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
6.40
5.00
10.00
17.00
0.46
7.50

1SNC165023S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM70/31.AF stud terminal blocks
Feed-through - 31 mm 1.220 in spacing
50 mm²0 AWG

Description–– Compact one stud / one clamp terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

Ordering details
1SNC165011F0014

Description

Color

Type

Part Number

Pkg
pce

Feed-through1 stud M8 + 1 screw clamp

M70/31.AF

Grey

1SNA115142R1100

Main technical data

10

Weight(1 pce) g
110.00

Mounting instructions

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

M70/31.AF

NFC

DIN

UL
2.5-70 mm² 8-0 AWG

6-70 mm²6-50 mm²C5

2.5-50 mm²

CSA
6-0 AWG

Rail
Lugs
Tool

IEC
DIN
UL
6-70 mm² 6-70 mm² 8-0 AWG
6-50 mm²

CSA
6-0 AWG

IEC

DIN

UL

CSA

Torque

150 A
50 mm²1000 V
8000 V

178 A
50 mm²

150 A
0 AWG
600 V

200 A
0 AWG
600 V

Screw clamp
Tool

TorqueG32, TH 35-7.5,
TH 35-15
WrenchH13 mm6-12 N.m
53.1-106.2 lb.in

Jumper screw
Tool

66 2.60"
78 3.08"70.5 2.78"

75.5 2.50"

22 0.87"

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

TorqueWire stripping
length

34 1.34"
39 1.54"

4

WrenchH13 mm7 ± 1 N.m
61.9 ± 8.85 lb.in
22 mm
0.866 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

31 mm 1.220 in spacing

RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers

End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP31
CPP311
CPP312
CPP313PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113690R2100
1SNA168204R1500
1SNA168203R1400
1SNA163409R0600
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
6.70
7.00
14.00
23.00
0.46
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165024S0201 - Rev. B

3

Color

Technical data valid for copper conductors only.

PAGE 89

M120/35.AF stud terminal blocks
Feed-through - 35 mm 1.380 in spacing
Description

70 mm²250 Kcmil–– Compact one stud / one clamp terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

Ordering details
1SNC165013F0014

Description

Color

Feed-through1 stud M8 + 1 screw clamp

85 3.35"
77.5 3.05"

82.5 3.25"
34 1.34"
39 1.54"

M120/35.AF

Grey

1SNA115145R1400

Main technical data

Pkg
10

Weight(1 pce) g
160.00

Mounting instructions
NFC

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

69 2.72"
27 1.06"

Part Number

pceM120/35.AF

4

Type

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

6-95 mm²
6-70 mm²
C6

DIN

UL
CSA
Rail
2.5-70 mm² 2-250 Kcmil max 000 AWG
2.5-70 mm²
Lugs
Tool

IEC
DIN
UL
35-120 mm² 35-120 mm² 2-250 Kcmil
35-70 mm² 35-70 mm²CSA
2-000 AWG

TorqueG32, TH 35-7.5,
TH 35-15
WrenchH13 mm6-12 N.m
53.1-106.2 lb.in

Tool
IEC

DIN

UL

CSA

192 A
70 mm²1000 V
8000 V

150 A
50 mm²255 A
250 Kcmil
600 V

270 A
000 AWG
600 V

TorqueScrew clamp
Tool
TorqueWire stripping
length

WrenchH13 mm7 ± 1 N.m
61.9 ± 8.85 lb.in
28 mm
1.102 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

35 mm 1.380 in spacing

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP35
CPP351
CPP352
CPP353PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113691R1600
1SNA168206R1700
1SNA168205R1600
1SNA163418R2600
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
10.00
8.00
20.00
20.00
0.46
7.50

1SNC165025S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM300/42.AF stud terminal blocks
Feed-through - 42 mm 1.653 in spacing
120 mm²
500 Kcmil

Description–– Compact one stud / one clamp terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

Ordering details
1SNC165013F0014

Description

Color

Type

Part Number

Pkg
pce

Feed-through1 stud M10 + 1 screw clamp

M300/42.AF

Grey

1SNA115148R2700

Main technical data

10

Weight(1 pce) g
340.00

Mounting instructions
NFC

DIN

UL
0-500 Kcmil

CSA
0-500 Kcmil

Rail

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

50-150 mm² 6-150 mm²50-120 mm² 6-120 mm²
C8

Screw clamp

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

IEC
DIN
UL
CSA
Torque70-300 mm² 70-300 mm² 0-500 Kcmil 0-500 Kcmil
70-120 mm² 70-120 mm²
Jumper screw
Tool

M300/42.AF

Lugs
Tool

G32, TH 35-7.5,
TH 35-15
WrenchH16 mm
10-20 N.m
88.5-177 lb.in

93 3.66"
107 4.22"
99.5 3.92"

104.5 4.12"

35 1.38"

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

IEC

DIN

UL

CSA

269 A
120 mm²
1000 V
8000 V

269 A
120 mm²

380 A
500 Kcmil
600 V

550 A
500 Kcmil
600 V

Screw clamp
Tool
TorqueWire stripping
length

46 1.81"
51 2.01"

Torque4

WrenchH16 mm11 ± 1 N.m
97.36 ± 8.85 lb.in
40 mm
1.575 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

42 mm 1.653 in spacing

RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Blank card

End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP42
CPP421
CPP422
CPP423PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113692R1700
1SNA168208R2100
1SNA168207R1000
1SNA163424R1400
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
20.00
13.00
30.00
40.00
0.46
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165026S0201 - Rev. B

3

Color

Technical data valid for copper conductors only.

PAGE 91

M35/26.F stud terminal blocks
Feed-through - 26 mm 1.024 in spacing
Description

25 mm²–– Compact one stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

2 AWG

1SNC165012F0014

Ordering details
Description

Color

Type

Feed-through1 stud M6

60 2.37"57.5 2.27"

1SNA115141R1000

Main technical data

10

Weight(1 pce) g
40.00

Mounting instructions

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

66 2.60"

52.5 2.07"

M35/26.F

Grey

NFC

DIN

4-35 mm²4-25 mm²C3

2.5-25 mm²

IEC

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

UL
2.5-50 mm² 10-2 AWG

DIN

UL

CSA
Rail
max 4 AWG
Lugs
Tool

G32, TH 35-7.5,
TH 35-15
Wrench
H10 mm

CSA

4.5-9 N.m
39.8-79.6 lb.in

TorqueJumper screw
Tool

IEC

DIN

UL

CSA

Torque

101 A
25 mm²1000 V
8000 V

125 A
35 mm²

115 A
2 AWG
600 V

125 A
4 AWG
600 V

Screw clamp
Tool
TorqueWire stripping
length33.5 1.32"
38.5 1.52"

26 mm 1.024 in spacing

Pkg
pce

M35/26.F

4Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP26
CPP261
CPP262
CPP263PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113689R2400
1SNA168202R1300
1SNA168201R1200
1SNA163403R2000
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
6.40
5.00
10.00
17.00
0.46
7.50

1SNC165015S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM70/31.F stud terminal blocks
Feed-through - 31 mm 1.220 in spacing
Description

50 mm²–– Compact one stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

00 AWG

1SNC165018F0014

Ordering details
Description

Color

Type

Feed-through1 stud M865.5 2.58

1SNA115144R1300

Main technical data

10

Weight(1 pce) g
60.00

Mounting instructions

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

66 2.60"

63 2.48"

M70/31.F

Grey

NFC

DIN

6-70 mm²6-50 mm²C5

2.5-50 mm²

IEC

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

UL
2.5-70 mm² 4-00 AWG

DIN

UL

CSA
Rail
max 0 AWG
Lugs
Tool

G32, TH 35-7.5,
TH 35-15
WrenchH13 mm

CSA

6-12 N.m
53.1-106.2 lb.in

TorqueJumper screw
Tool

IEC

DIN

UL

CSA

Torque

150 A
50 mm²1000 V
8000 V

150 A
50 mm²175 A
00 AWG
600 V

200 A
0 AWG
600 V

Screw clamp
Tool

4

TorqueWire stripping
length

34 1.34"
39 1.54"

Pkg
pce

M70/31.F

58 2.28"

Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

31 mm 1.220 in spacing
RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers

End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP31
CPP311
CPP312
CPP313PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113690R2100
1SNA168204R1500
1SNA168203R1400
1SNA163409R0600
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
6.70
7.00
14.00
23.00
0.46
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165016S0201 - Rev. B

3

Color

Technical data valid for copper conductors only.

PAGE 93

M120/35.F stud terminal blocks
Feed-through - 35 mm 1.380 in spacing
Description

70 mm²250 Kcmil–– Compact one stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

1SNC165017F0014

Ordering details
Description

Color

Type

Feed-through1 stud M8

67 2.64"64.5 2.54"

1SNA115147R1600

10Weight(1 pce) g
61.00

Mounting instructions

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferruleGauge

69 2.72"

59.5 2.34"

M120/35.F

Grey

Main technical data

M120/35.F

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

DIN

6-95 mm²
6-70 mm²
C6

UL
CSA
Rail
2.5-70 mm² 2-250 Kcmil max 000 AWG
2.5-70 mm²
Lugs
Tool

G32, TH 35-7.5,
TH 35-15
WrenchH13 mmIEC

DIN

6-12 N.m
53.1-106.2 lb.in

UL

CSA

TorqueJumper screw
Tool

IEC

DIN

UL

CSA

192 A
70 mm²1000 V
8000 V

150 A
50 mm²255 A
250 Kcmil
600 V

270 A
000 AWG
600 V

TorqueScrew clamp
Tool
TorqueWire stripping
length

34 1.34"
39 1.54"

35 mm 1.380 in spacing

Pkg
pce

NFC

4

Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers
End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP35
CPP351
CPP352
CPP353PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113691R1600
1SNA168206R1700
1SNA168205R1600
1SNA163418R2600
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
10.00
8.00
20.00
20.00
0.46
7.50

1SNC165017S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM300/42.F stud terminal blocks
Feed-through - 42 mm 1.653 in spacing
120 mm²
500 Kcmil

Description–– Compact one stud terminal block,–– Lug mounting in accordance with NF C 20-130 and DIN 46234,–– Various marking options,–– Rail or base mounting.

1SNC165016F0014

Ordering details
Description

Color

Type

Part Number

pceFeed-through1 stud M10

M300/42.F

Grey

1SNA115150R2500

Main technical data
M300/42.F

46 1.81"

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Screw clamp

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

NFC

DIN

UL
CSA
Rail
50-150 mm² 6-150 mm² 0-500 Kcmil max 500 Kcmil
50-120 mm² 6-120 mm²
Lugs
C8
Tool

G32, TH 35-7.5,
TH 35-15
WrenchH16 mmIEC

DIN

10-20 N.m
88.5-177 lb.in

UL

CSA

TorqueJumper screw
Tool

IEC

DIN

UL

CSA

269 A
120 mm²
1000 V
8000 V

269 A
230 A
120 mm² 500 Kcmil
600 V

550 A
500 Kcmil
600 V

Torque4

Screw clamp
Tool
Torque51 2.01"

42 mm 1.653 in spacing

10

Weight(1 pce) g
100.00

Mounting instructions

Lugs

71 2.80"
63.5 2.50"

68.5 2.70"

93 3.66"

Pkg

Wire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

CSA

Gost R

Accessories
Description
1

2

Type

Part Number

Pkg
pce

1
2
3

4
4

9.1 mm0.358 in
10 mm
0.394 inCircuit separators Circuit separators
Protecting covers
marked cut: 2 blocks
marked cut: 3 blocks
Terminal block
Label holder
markers
Terminal block markers

End stops

Grey
Dark grey
GreyTransparent

Grey
White

BAMH
BAZH1
ECP42
CPP421
CPP422
CPP423PEP
RC610

1SNA114836R0000
1SNK900102R0000
1SNA113692R1700
1SNA168208R2100
1SNA168207R1000
1SNA163424R1400
1SNA113762R2400
1SNA233000R0100

50
20
10
5
5
5
50
1

Weight(1 pce) g
13.00
24.00
20.00
13.00
30.00
40.00
0.46
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165018S0201 - Rev. B

3

Color

Technical data valid for copper conductors only.

PAGE 95

TE Connectivity's "positive retention" lock footMounting instructions
Mounting
The locking action is automatic on mounting the block on the rail.

Unlocking–– Pull or push on the locking tag, using pliers as follows,–– Blocks mounted on DIN 1 rail: pull on the release tag,–– Blocks mounted on DIN 3 rails: push on the release tag,–– Remove the block from the rail by rotation, using a tube wrench
Automatic locking on rail

while maintaining the action of the pliers.

Automatic locking on rails

Locking tag

Space requirements of blocks with their partition or protective coverPartition for TYPE I blocks.
Part Number

Spacing A

B

C

D

E

F

40.5
44.5
47.5
60.5

67.5
72.5
82.5
104.5

62.5
67.5
77.5
99.5

70
75
85
107

F

Type

A

ECP26
ECP31
ECP35
ECP42

1SNA113689R2400
1SNA113690R2100
1SNA113691R1600
1SNA113692R1700

26
31
35
42

76
84
90
116

35.5
39.5
42.5
55.5

D

Dimensions mm

E
BC

Marker-holder for power blocks

This marker-holder snaps on the ECP and ECS power blocks
partitions, as well as on the type I power blocks compression clamps.

TypePart Number

PEP

1SNA113762R2400

They can also be mounted on the SCF separator end sections.

This marker-holder can receive:
1 label 		
RC610

Adhesive marker

High performance adhesive marker for most surface types.
See section on markers.
TypePart Number

RPA

1SNA235463R2300

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

1SNC165027S0201

41SNC165027S0201

4

PAGE 97

1SNC168014S0201

5

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Ring lug technology
Overview			

100

Feed-through		
6 mm² / 8 AWG

101

M6/9.EE		

102

M6/12.FF		
M6/13.FF		

103 to 104

Feed-through		
16 mm²105		

165LTTM5TM5		

Test disconnect		
165ETTM5TM5

With a screwdriver sliding link

106		

165ETTM5TM5-2

With a screwdriver sliding link and test

107

5

1SNC168014S0201

16 mm²

PAGE 99

Dedicated applications terminal blocks
Ring lug technology

Feed-throughSectionIEC

UL/CSA

6 mm²

8 AWG

M6/9.EE

M6/12.FF

M6/13.FF

9.5 mm 0.374 in

12.5 mm 0.492 in

13 mm 0.512 in5

Feed-throughTest disconnect

SectionIEC

UL/CSA

165LTTM5TM5165ETTM5TM5165ETTM5TM5-2

16 mm 0.630 in

16 mm 0.630 in

16 mm 0.630 in

1SNC168015S0201

16 mm²

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM6/9.EE ring lug terminal blocks
Feed-through - 9.5 mm 0.374 in spacing
Description

6 mm²–– Strap screw terminal block for ring lug connection,–– Removable partition for jumpering.

8 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC168009F0014

Feed-throughGrey

42.5 1.67"

50

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

IEC
0.5-6 mm²
0.5-6 mm²UL
22-8 AWG

41 A
6 mm²
800 V
8 kV

40 A
22-8 AWG
600 V

CSA
max 8 AWG

Rail
Lugs
Tool

40 A
8 AWG
600 V

NEMA

TorqueG32, TH 35-7.5,
TH 35-15
Flat screwdriver
6.35 mm
0.250 in
0.8 - 1 N.m
7.1 - 8.9 lb.in

Wire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

CSA

EAC

35 1.38"

40 1.58"

1SNA115201R2500

Mounting instructions

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
Protection

41 1.61"

M6/9.EE

Main technical data
Lugs

M6/9.EE

With 2 screws
CL 6-32 NC - 2A
DIA 3.5 mm 0.138 infor lug max width
8.5 mm 0.334 in

Weight(1 pce) g
7.00

5

14.5 0.57"
19.5 0.77"

9.5 mm 0.374 in spacing

Accessories
Description
1

2Part Number

Pkg

1

4
4
5

10 mm
5.2 mmEnd sections
3 mm
Jumper bars
2 poles
3 poles
4 poles
10 polesCircuit separators 1 mm
Terminal block
Blank card
markers

End stops

0.394 in
0.205 in
0.118 in
41 A

Dark grey

0.039 in

White

Grey

White

BAM4
BAZ1
FEM9
BJS9.5-2
BJS9.5-3
BJS9.5-4
BJS9.5-10
SCF9
RCT810

1SNK900001R0000
1SNK900002R0000
1SNA113067R1700
1SNA173815R1600
1SNA173816R1700
1SNA173817R1000
1SNA173819R2200
1SNA103672R0100
1SNA236500R0600

50
50
1
10
10
10
10
20
1

Weight(1 pce) g
14.00
5.30
2.40
1.00
1.60
2.20
5.60
2.00
7.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC168001S0201 - Rev. B

5

Type

pce

2
3
3

Color

Technical data valid for copper conductors only.

PAGE 101

M6/12.FF ring lug terminal blocks
Feed-through - 12.5 mm 0.492 in spacing
Description

6 mm²–– Terminal block for high vibration environment,–– Stud connection,–– Removable partition for jumpering.

8 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

M6/12.FF
M6/12.FF

1SNA115263R2200
1SNA400753R1000

50
50

Weight(1 pce) g
20.00
20.00

M6/12.FF
M6/12.FF1

1SNA115511R0300
1SNA115262R2100

50
50

13.00
13.00

1SNC168010F0014

pce

Feed-throughM6/12.FFWith nuts, with 2 studs
8-32 UNC - 2A
DIA 4.16 mm 0.164 in,height 9 mm 0.354 in,for lug max
width 9.5 mm 0.374 in
Without nuts, with 2 studs
8-32 UNC - 2A
DIA 4.16 mm 0.164 in,height 9 mm 0.354 in,for lug max
width 9.5 mm 0.374 in

White

Grey

Grey
White

Main technical data
43 1.69"
42.5 1.67"
35 1.38"

40 1.58"

Lugs

5

16.5 0.65"

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
ProtectionIECmax 6 mm²

UL
8 AWG

41 A
6 mm²
800 V
8 kV

40 A
8 AWG
600 V
NEMA

CSA
Rail
18-10 AWG
Lugs
Tool
25 A
10 AWG
Torque600 V
Wire stripping
lengthG32, TH 35-7.5,
TH 35-15
Wrench
1.8 N.m
15.65 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

21.5 0.85"
C

RoHS

USR

US

cCSAus

EAC

12.5 mm 0.492 in spacing

Accessories
Description
1

2

4

5

6

Type

Part Number

Pkg
pce

1
2
3

3

Color

4
5
6

10 mm
5.2 mmEnd sections
3 mm
Jumper bars
2 poles
3 poles
5 poles
10 polesCircuit separators 1 mm
Nuts
Terminal block
Blank card
markers
End stops

0.394 in
0.205 in
0.118 in
41 A

Dark grey

0.039 in

White

Grey

White

BAM4
BAZ1
FEM12F
BJS12.5-2
BJS12.5-3
BJS12.5-5
BJS12.5-10
SCF9
ECR-3
RCT810

1SNK900001R0000
1SNK900002R0000
1SNA116713R1600
1SNA174393R2000
1SNA174394R2100
1SNA174395R2200
1SNA174396R2300
1SNA103672R0100
1SNA175263T0600
1SNA236500R0600

50
50
25
10
10
10
10
20
100
1

Weight(1 pce) g
14.00
5.30
1.25
1.70
2.70
4.80
9.90
2.00
1.00
7.60

1SNC168002S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM6/13.FF ring lug terminal blocks
Feed-through - 13 mm 0.512 in spacing
Description

6 mm²–– Two stud terminal block for ring lug connection,–– Removable partition for jumpering.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC168016F0014

Feed-throughWith 2 studs M4 x 16

Grey

1SNA115626R1600

Main technical data
Lugs

25

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
Protection

M6/13.FF

M6/13.FF

Weight(1 pce) g
16.00

IEC
max 6 mm²
max 6 mm²

UL
10 AWG

41 A
6 mm²
800 V
8 kV

35 A
10 AWG
600 V
NEMA

CSA
Rail
18-10 AWG
Lugs
Tool
25 A
18-10 AWG
Torque600 V
Wire stripping
lengthG32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 6.35 mm
Ø 0.250 in
1.2 - 2.5 N.m
10.6 - 21.8 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

51.5 2.03"
48 1.89"

USR

US

cCSAus

EAC

40.5 1.59"

45.5 1.79"

C

RoHS

5
24.5 0.97"
29.5 1.61"

13 mm 0.512 in spacing

Accessories
Description
1

3

2

4

Color

Type

Part Number

Pkg
pce

1

End stops

10 mm
5.2 mm
1 mm
10 poles23
4
5

End sections
Jumper bars
Protecting covers
Terminal block markers Blank card

0.394 in
0.205 in
0.039 in
125 A

Dark grey
Grey

White

BAM4
BAZ1
FEM13F
BJS13-10
CPE43
RC1010

1SNK900001R0000
1SNK900002R0000
1SNA116977R1700
1SNA167224R2700
1SNA280092R2500
1SNA238000R1600

50
50
25
10
2
1

Weight(1 pce) g
14.00
5.30
1.40
10.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC168003S0201 - Rev. B

5

Technical data valid for copper conductors only.

PAGE 103

M6/13.FF ring lug terminal blocks
Feed-through - 13 mm 0.512 in spacing
Description

6 mm²–– Two stud terminal block for ring lug connection,–– Removable partition for jumpering.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC168015F0014

Feed-throughWith 2 studs M5 x 16

Grey

1SNA115627R1700

Main technical data
Lugs

25

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
Protection

M6/13.FF

M6/13.FF.1

Weight(1 pce) g
16.00

IEC
max 10 mm²
max 10 mm²

UL
8 AWG

57 A
10 mm²
800 V
8 kV

50 A
8 AWG
600 V
NEMA

CSA
Rail
18-10 AWG
Lugs
Tool
25 A
18-10 AWG
Torque600 V
Wire stripping
lengthG32, TH 35-7.5,
TH 35-15
Wrench
H8 mm
0.310 in
2 - 4 N.m
17.7 - 35.4 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

51.5 2.03"
48 1.89"

USR

US

cCSAus

EAC

40.5 1.59"

45.5 1.79"

C

RoHS

5
24.5 0.97"
29.5 1.61"

13 mm 0.512 in spacing

Accessories
Description
1

3

2

4

Color

Type

Part Number

Pkg
pce

1

End stops

10 mm
5.2 mm
1 mm
13 mm

2
3
4
5

End sections
Jumper bars
Protecting covers
Terminal block markers Blank card

0.394 in
0.205 in
0.039 in
125 A

Dark grey
Grey

White

BAM4
BAZ1
FEM13F
BJS13-10
CPE43
RC1010

1SNK900001R0000
1SNK900002R0000
1SNA116977R1700
1SNA167224R2700
1SNA280092R2500
1SNA238000R1600

50
50
25
10
2
1

Weight(1 pce) g
14.00
5.30
1.40
10.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC168004S0201 - Rev. B

5

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

165LTTM5TM5 ring lug terminal blocks
Feed-through - 16 mm 0.630 in spacing
Description

16 mm²–– Two stud terminal block for ring lug connection,–– Profile aligned with disconnect terminal blocks type 165ETTM5TM5.

Ordering details
1SNC168034F0014

Description

Color

Feed-through

WIth 2 studs M5 x 16
and partition

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
Protection
56.5 2.23"

Grey

165LTTM5TM5

1SNA216110R2200

Main technical data

165LTTM5TM5

Pkg
25

Weight(1 pce) g
40.00

Mounting instructionsIEC
16 mm²16 mm²

UL
6 AWG

76 A
16 mm²
800 V
8 kV

65 A
6 AWG
600 V

CSA

Rail
Lugs
Tool

NEMA

TorqueG32, TH 35-7.5,
TH 35-15
Wrench
H8 mm
0.310 in
2 - 4 N.m
17.7 - 35.4 lb.in

Wire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR

EAC

49 1.92"

54 2.13"

Part Number

pce

Lugs

74 2.91"Type

37 1.46"5

42 1.65"

16 mm 0.630 in spacing

Accessories
Description
1

3

2

4

Color

Type

Part Number

Pkg
pce

1
2
3
4
5

10 mm
0.079 in
5.2 mm0.205 inEnd sections
2 mm
0.079 in
Test sockets
DIA 4 mm 0.157 inProtecting covers Length 2 m 78 in
Terminal block markers Blank card
End stops

Dark grey
Grey

BAM4
BAZ1
FEET80
AL4-M3-R1
CPE80
REH3

1SNK900001R0000
1SNK900002R0000
1SNA216114R1200
1SNA206722R0200
1SNA280093R2600
1SNA163155R2600

50
50
10
50
1
1

Weight(1 pce) g
14.00
5.30
7.20
1.62
103.0020.00

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC168007S0201 - Rev. B

5

Technical data valid for copper conductors only.

PAGE 105

165ETTM5TM5 ring lug terminal blocks
Test disconnect with a screwdriver sliding link - 16 mm 0.630 in spacing
Description

16 mm²–– Secure your disconnect operations with the disconnect sliding link operated with a screwdriver,–– Two stud terminal block for ring lug connection,–– Profile aligned with terminal blocks type 165LTTM5TM5.

Ordering details
1SNC168035F0014

Description

Color

Type

Part Number

Disconnect

With 2 studs M5 x 18
fitted with 1 nut + 1 lockwasher

Grey

165ETTM5TM5

1SNA216112R1000

Main technical data
165ETTM5TM5

Pkg
pce

Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
Protection

25

Weight(1 pce) g
22.00

Mounting instructionsIEC
16 mm²16 mm²

UL

CSA

Rail
Lugs
Tool

76 A
16 mm²800 V
8 kV

TorqueNEMA

Disconnect device
Tool
TorqueG32, TH 35-7.5,
TH 35-15
Wrench
H8 mm
0.310 in
2 - 4 N.m
17.7 - 35.4 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Wire stripping
length16 mm 0.630 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5
RoHS

EAC

Accessories
Description
1

3

2

4

Color

Type

Part Number

Pkg
pce

1
2
3
4
5

10 mm
0.079 in
5.2 mm0.205 inEnd sections
2 mm
0.079 in
Test sockets
DIA 4 mm 0.157 inProtecting covers Length 2 m 78 in
Terminal block markers Blank card
End stops

Dark grey
Grey

BAM4
BAZ1
FEET80
AL4-M3-R1
CPE80
REH3

1SNK900001R0000
1SNK900002R0000
1SNA216114R1200
1SNA206722R0200
1SNA280093R2600
1SNA163155R2600

50
50
10
50
1
1

Weight(1 pce) g
14.00
5.30
7.20
1.62
103.0020.00

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through wire lug terminal blocks
Description

Color

Type

Part Number

Pkg
pce

Feed-throughTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey

165LTTM5TM5

1SNA216110R2200

25

Weight(1 pce) g
40.00

1SNC168010S0201 - Rev. B

5

165ETTM5TM5 ring lug terminal blocks
Test disconnect with a screwdriver sliding link - 16 mm 0.630 in spacing
Description

16 mm²–– Secure your disconnect operations with the disconnect sliding link operated with a screwdriver,–– Ease your test operations with the 2 independent built-in test sockets compatible with DIA 4 mm 0.157 in test plugs,–– Two stud terminal block for ring lug connection,–– Profile aligned with terminal blocks type 165LTTM5TM5.
1SNC168033F0014

Ordering details

165ETTM5TM5

Description

Color

Type

Part Number

Pkg
pce

Disconnect

With 2 studs
M5 x 18 fittedwith 2 nuts + 1 washer,with test sockets
DIA 4 mm 0.157 in

Beige

165ETTM5TM5-2

1SNA296117R1600

Main technical data
Lugs

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Rated cross section
Rated voltage
Impulse withstand voltage
Protection

25

Weight(1 pce) g
51.00

Mounting instructionsIEC
16 mm²16 mm²

UL

CSA

Rail
Lugs
Tool

76 A
16 mm²800 V
8 kV

TorqueNEMA

Disconnect device
Tool
TorqueG32, TH 35-7.5,
TH 35-15
Wrench
H8 mm
0.310 in
2 - 4 N.m
17.7 - 35.4 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Wire stripping
length16 mm 0.630 in spacing

5

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

Accessories
Description

3

Type

Part Number

Pkg
pce

2

1

4

2
3
4

10 mm
0.079 in
5.2 mm0.205 inEnd sections
2 mm
0.079 inProtecting covers Length 2 m 78 in
Terminal block markers Blank card
End stops

Dark grey
Beige

BAM4
BAZ1
FEET80CPE80
REH3

1SNK900001R0000
1SNK900002R0000
1SNA296114R1300
1SNA280093R2600
1SNA163155R2600

50
50
10
1
1

Weight(1 pce) g
14.00
5.30
7.20
103.0020.00

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC168012S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

PAGE 107

1SNC160099S0201

6

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Miniblocks
Overview						

110Screw clamp technology		
Rail TH 35		Feed-through4 mm² / 10-12 AWG

MS4/6		

112

6 mm² / 8 AWG

MS6/8		

113

Rail TH 15		Feed-through

1.5 mm² / 12 AWG

		

DR1.5/4		

114

DR1.5/5		

115

4 mm² / 10-12 AWG

DR4/6		

117

Ground4 mm² / 10-12 AWG

DR4/6.P		

119

Disconnect
Fuse

2.5 mm² / 12 AWG
4 mm² / 12 AWG

DR2.5/5.S		
DR4/8.SF		

120
121

Spring clamp technology		
Rail TH 35		Feed-through

2.5 mm² / 12 AWG

		

DS2.5/5.2L

2 connections

122

DS2.5/10.4L

4 connections

123

Rail TH 15
Feed-throughDR2.5/5.2L

2 connections

124

		

2.5 mm² / 12 AWG

DR2.5/10.4L

4 connections

125

Ground

DR2.5/10.P.4L

4 connections

126

DB2.5/5.2L
DH2.5/5.2L

2 connections with flanges mounting
2 connections with snap in foot

127
128

2.5 mm² / 12 AWG

Base mounting
Feed-through 2.5 mm² / 12 AWG		ADO / screw clamp technology		
Rail TH 35
Feed-throughGround1 mm² / 18 AWG

DS2.5/5.ADO & DSE2.5/5.ADO

129

1.5 mm² / 16 AWG

DS4/6.ADO & DSE4/6.ADO

130

2.5 mm² / 14 AWG

DS4/8.ADO & DSE4/8.ADO

131

2.5 mm² / 14 AWG

DS4/8.P.ADO		

132

1 mm² / 18 AWG

DR2.5/5.ADO & DRE2.5/5.ADO

133

1.5 mm² / 16 AWG

DR4/6.ADO & DRE4/6.ADO

134

2.5 mm² / 14 AWG

DR4/8.ADO & DRE4/8.ADO

135

2.5 mm² / 14 AWG

DR4/8.P.ADO		

136

1 mm² / 18 AWG

DB2.5/5.ADO

With flanges mounting

137

1.5 mm² / 16 AWG

DB4/6.ADO

With flanges mounting

138

2.5 mm² / 14 AWG
1.5 mm² / 16 AWG

DB4/8.ADO
DH4/6.ADO

With flanges mounting
With snap in foot

139
140

6

Rail TH 15
Feed-throughGroundBase mounting
Feed-throughADO / ADO technology		
Rail TH 35
Feed-throughGround

1.5 mm² / 16 AWG

DS1.5/6.ADO & DSE1.5/6.ADO

141

2.5 mm² / 14 AWG

DS2.5/8.ADO & DSE2.5/8.ADO

142

2.5 mm² / 14 AWG

DS2.5/8.P.ADO

143

1 mm² / 18 AWG

DR1/5.ADO & DRE1/5.ADO

144

1.5 mm² / 16 AWG

DR1.5/6.ADO & DRE1.5/6.ADO

145

2.5 mm² / 14 AWG

DR2.5/8.ADO & DRE2.5/8.ADO

146

2.5 mm² / 14 AWG

DR2.5/8.P.ADO		

147

1.5 mm² / 16 AWG

DB1.5/6.ADO

With flanges mounting

148

2.5 mm² / 14 AWG
1.5 mm² / 16 AWG

DB2.5/8.ADO
DH1.5/6.ADO

With flanges mounting
With snap in foot

149
150

Feed-throughGroundBase mounting
Feed-through

PAGE 109

1SNC160099S0201

Rail TH 15

Dedicated applications terminal blocks
Miniblocks

Screw clamp technology

Feed-throughGroundDisconnect

Fuse

SectionIEC

UL/CSA

1.5 mm²

12 AWG

DR1.5/4
4 mm 0.157 in

1.5 mm²

12 AWG

DR1.5/5
5 mm 0.197 in

2.5 mm²

12 AWG

DR2.5/5 S
5.08 mm 0.200 in

4 mm²
6 mm²

10-12 AWG
8 AWG

MS4/6

DR4/6

DR4/6.P

DR4/8.SF

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

8 mm 0.315 in

TH 15

TH 15

MS6/8
8 mm 0.315 inRail / mounting

TH 35

TH 15

TH 15

6

Spring clamp technology

Feed-throughGroundSectionIEC

UL/CSA

2.5 mm²

12 AWG

2.5 mm²

12 AWG

DR2.5/5.2L

DB2.5/5.2L

DH2.5/5.2L

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

DS2.5/10.4L

DR2.5/10.4L

10 mm 0.394 in

10 mm 0.394 in

TH 35

TH 15

DR2.5/10.P.4L
10 mm 0.394 in

BASE

BASE

TH 15

1SNC160061S0201

Rail / mounting

DS2.5/5.2L
5 mm 0.197 in

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSADO / screw clamp technology

Feed-throughGroundSectionIEC

UL/CSA

1 mm²

18 AWG

1.5 mm²
2.5 mm²

16 AWG
14 AWG

Rail / mounting

DS2.5/5.ADO

DR2.5/5.ADO

DB2.5/5.ADO

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

DS4/6.ADO

DR4/6.ADO

DB4/6.ADO

DH4/6.ADO

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

DS4/8.ADO

DR4/8.ADO

DB4/8.ADO

DS4/8.P.ADO

DR4/8.P.ADO

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

TH 35

TH 15

BASE

TH 35

TH 15

BASE

6

ADO / ADO technology

Feed-throughGroundSectionIEC

UL/CSA

1 mm²

18 AWG

DR1/5.ADO
5 mm 0.197 in

2.5 mm²

16 AWG
14 AWG

Rail / mounting

DS1.5/6.ADO

DR1.5/6.ADO

DB1.5/6.ADO

DH1.5/6.ADO

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

DS2.5/8.ADO

DR2.5/8.ADO

DB2.5/8.ADO

DS2.5/8.P.ADO

DR2.5/8.P.ADO

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

8 mm 0.315 in

TH 35

TH 15

BASE

TH 35

TH 15

BASE

1SNC160061S0201

1.5 mm²

PAGE 111

MS4/6 screw clamp terminal blocks
Miniblocks - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Save space with compact over-all dimensions terminal block,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

1SNC161149F0014

Miniblocks

Color
Feed-throughGrey
Yellow

TypePart Number

MS4/6
MS4/6

1SNA115265R2400
1SNA105265R0300

Main technical data
Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

46 1.81"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

6.00
6.00

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-10 AWG

22-12 AWG

Wire stripping
length10 mm
0.39 inTool

Flat screwdriverØ 4 mmØ 0.157 in

32 A / 4 mm²
480 A
630 V
4000 V
IP20

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

30 A / 10 AWG 25 A / 12 AWG
600 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

38.5 1.51"

43.5 1.71"

100
100

UL

MS4/6

41 1.61"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

CE

RoHS

USR

CSA

Gost R

14.5 0.57"
19.5 0.77"

66 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 in
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
Circuit separators 2.4 mm
0.094 in
3 mm
0.118 in
Test adapters
Test plugs
DIA 2 mm 0.079 inProtecting covers Length 1 m 39 in
Terminal block markers
End stops

Color
Dark grey
Grey
Grey

Grey
Yellow
Black
Transparent
White

Type
BAM4
BAZ1
FEMS6
PC6-2
PC6-3
PC6-4
PC6-10EIPSCFEX3SCFCV1-2
DCJ
FC2
CPV1-2
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA113885R0100
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA103620R0100
1SNA116795R1100
1SNA173059R0300
1SNA007865R2600
1SNA176816R1200
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
100
1
1

14.00
5.30
1.80
2.00
2.00
1.00
8.00
30.00
8.00
2.40
7.50

1SNC161124S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

9Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSMS6/8 screw clamp terminal blocks
Miniblocks - 8 mm 0.315 in spacing
6 mm²
8 AWG

Description–– Save space with compact over-all dimensions terminal block,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

1SNC161148F0014

Miniblocks

Color
Feed-through

Type
Grey

Part Number

MS6/8

1SNA115278R0100

Main technical data
Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

54 2.12"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

12.00

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-8 AWG

20-8 AWG

Wire stripping
length

12 mm
0.47 inTool

Flat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in

41 A / 6 mm²
720 A
500 V
6000 V
IP20

Torque0.8 - 1 Nm
7.1 - 8.9 lb.in

50 A / 8 AWG

40 A / 8 AWG

300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

46.5 1.83"

51.5 2.03"

50

UL

MS6/8

41 1.61"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

CE

RoHS

USR

CSA

Gost R

14.5 0.57"
19.5 0.77"

68 mm 0.315 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

4

8

Dark grey
Grey

Grey
OrangeBlack
Transparent
White

Type
BAM4
BAZ1
FEMS8
PC8-2
PC8-3
PC8-4
PC8-10SCFEX3SCFCV1-2
DCO
FC2
CPV1-2
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA114195R0600
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA103620R0100
1SNA116795R1100
1SNA173060R0000
1SNA007865R2600
1SNA176816R1200
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
25
10
10
10
10
10
10
10
100
1
1

14.00
5.30
1.90
3.00
4.00
6.00
14.00
30.00
8.00
2.30
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161139S0201 - Rev. A

7

5
6
7
8

10 mm
0.394 in
5.2 mm0.205 inEnd sections
3 mm
0.118 in
Lateral jumper bars 2 poles
50 A
3 poles
4 poles
10 polesCircuit separators 2.4 mm
0.094 in
3 mm
0.118 in
Test adapters
Test plugs
DIA 2 mm 0.079 inProtecting covers Length 1 m 39 in
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 113

DR1.5/4 screw clamp terminal blocks
Miniblocks - 4 mm 0.157 in spacing
1.5 mm²

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

1SNC161141F0014

Miniblocks

DR1.5/4

Color
Feed-through

GreyPart Number

DR1.5/4

1SNA110106R2500

Main technical data
1 conductor
per clamp

Pkg

Weightpce(1 pce) g

50

3.00

Mounting instructions
IEC

UL

CSA

Rigid: Solid/Stranded
0.2-1.5 mm²
Flexible without ferrule 0.22-1.5 mm²
Flexible with insulated ferrule
Gauge
A1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

28 1.10"Type

17.5 A / 1.5 mm²
180 A
500 V
6000 V
IP20
NEMA 1

Rail

TH 15-5.5

Wire stripping
length7 mm
0.275 inTool

Flat screwdriverØ 2.5 mm
Ø 0.98 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
31 1.22"CE

RoHS

Gost R6
4 mm 0.157 in spacing

Accessories
Description
1

3

2

1
2
3

4
4
5

0.256 in
0.039 in17.5 A

Grey

0.012 in

White

Grey

White

Type
BADRL
FED2-4BJM4SCDR61
RC410

Part Number
1SNA199420R2100
1SNA215580R2100
1SNA205735R0600
1SNA205736R0700
1SNA205737R0000
1SNA205738R1100
1SNA173016R1000
1SNA229000R1500

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
25
1

2.00
1.40
1.00
2.00
3.00
6.00
0.40
5.16

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161125S0201 - Rev. A

5

6.5 mm
1 mm
2 poles
3 poles
5 poles
10 polesCircuit separators 0.3 mm
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDR1.5/5 screw clamp terminal blocks
Miniblocks - 5 mm 0.197 in spacing
1.5 mm²
12 AWG

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

1SNC161255F0014

Miniblocks

Color
Feed-through

Type
Grey

Part Number

DR1.5/5

1SNA115510R1600

Main technical data

100

5.00

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-1.5 mm²
Flexible with insulated ferrule
Gauge

UL

CSA

Rail

TH 15-5.5

28 - 12 AWG

28 - 14 AWG

Wire stripping
length

8.5 mm0.335 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

DR1.5/5

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

27.5 1.08"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

20 A / 1.5 mm² 20 A / 12 AWG 20 A / 14 AWG
180 A
Torque
250 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 125 0.98"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R6

5 mm 0.197 in spacing

Accessories
Description
1

3

2

1
2
3

4
4
5

0.256 in
0.039 in
24 A

Grey
Grey

25 A
White

Type
BADRL
FEDR5
BJMI5DR

PC51-10
RC55

Part Number
1SNA199420R2100
1SNA117318R2300
1SNA176704R0200
1SNA176705R0300
1SNA176706R0400
1SNA176708R1600
1SNA167908R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
10
1

2.00
0.80
2.00
3.00
4.00
12.00
5.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161145S0201 - Rev. A

5

6.5 mm
1 mm
2 poles
3 poles
4 poles
10 poles
Lateral jumper bars 10 poles
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

PAGE 115

DR1.5/5 screw clamp terminal blocks
Miniblocks - 5 mm 0.197 in spacing
1.5 mm²
12 AWG

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

1SNC161301F0014

Miniblocks

Color
Feed-through with partition

Type
Grey

Part Number

DR1.5/5.1

1SNA112086R0200

Main technical data
UL

100

5.00

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-1.5 mm²
Flexible with insulated ferrule
Gauge

CSA

Rail

TH 15-5.5

28-14 AWG

Wire stripping
length

8.5 mm0.335 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

DR1.5/5

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

27.5 1.08"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

20 A / 1.5 mm²
180 A
250 V
IP20

20 A / 14 AWG
300 V
NEMA 125 0.98"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

CSA

Gost R

5 mm 0.197 in spacing

Accessories
Description
1

3

5

2

1
2
3

4
4
5

6.5 mm
1 mm
2 poles
3 poles
4 poles
10 poles20 poles
Lateral jumper bars 10 poles
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
0.256 in
0.039 in
24 A

Grey
Grey

25 A
White

Type
BADRL
FEDR5
BJMI5DR

BJS5-20
PC51-10
RC55

Part Number
1SNA199420R2100
1SNA117318R2300
1SNA176704R0200
1SNA176705R0300
1SNA176706R0400
1SNA176708R1600
1SNA177652R0600
1SNA167908R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
10
10
1

2.00
0.80
2.00
3.00
4.00
12.00
4.00
5.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161131S0201 - Rev. A

6

CE

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDR4/6 screw clamp terminal blocks
Miniblocks - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161099F0014

Miniblocks

Feed-throughDR4/6
DR4/6.N

Grey
Blue

1SNA110251R0500
1SNA120251R0700

Main technical data

Mounting instructions
IEC

1 conductor
per clamp

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

UL

CSA

Rail

TH 15-5.5

22 - 12 AWG

28-10 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

DR4/6

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

28 1.10"50
50Weight(1 pce) g
6.00
6.00

30 A / 4 mm²
480 A
500 V

250 V

IP20

NEMA 1

20 A / 12 AWG 25 A / 10 AWG
600 V

31 1.22"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

CE

RoHS

USR

US

cCSAusGost R6
6 mm 0.236 in spacing

Accessories
Description

2
1
2
3

3

5

4

6

4
5
6

Color

6.5 mm
1 mm
2 poles
3 poles
4 poles
10 poles
Lateral jumper bars 10 poles
Circuit separators 0.3 mm
Terminal block markers Blank card
End stops
End sections
Jumper bars

0.256 in
0.039 in
32 A

Grey

BADRL
FEDR61
BJM62

White

PC61-10SCDR61
RC65

Grey

35 A
0.012 in

Type

White

Part Number
1SNA199420R2100
1SNA117600R0300
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173226R2700
1SNA163311R2200
1SNA173016R1000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
10
25
1

2.00
0.80
2.00
3.00
4.00
10.00
5.00
0.40
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with DR4/6...

Green-yellow

Type
DR4/6.PPart Number
1SNA160496R2600

Pkg

Weightpce(1 pce) g

50

10.00

Technical data valid for copper conductors only.

PAGE 117

1SNC161126S0201 - Rev. A

1

DR4/6.1 screw clamp terminal blocks
Miniblocks - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

1SNC161205F0014

Miniblocks

Color

Part Number

DR4/6.1

1SNA110491R1700

50

6.00

Feed-throughBlue

DR4/6.1.N

1SNA120491R1100

50

6.00

Mounting instructions

31 1.22"

UL

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-4 mm²
Flexible with insulated ferrule
Gauge

30 A / 4 mm²
480 A
500 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

28 1.10"Weight(1 pce) g

Grey

IEC

DR4/6.1

Pkg
pce

Feed-through withpartition

Main technical data
1 conductor
per clamp

CSA

Rail

TH 15-5.5

28-10 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

25 A / 10 AWG
600 V

IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

CE

RoHS

US

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

1
2
3

4

6

4
5
6

Color

6.5 mm
1 mm
2 poles
3 poles
4 poles
10 poles
Lateral jumper bars 10 poles
Circuit separators 0.3 mm
Terminal block markers Blank card
End stops
End sections
Jumper bars

0.256 in
0.039 in
32 A

Grey

BADRL
FEDR61
BJM62

White

PC61-10SCDR61
RC65

Grey

35 A
0.012 in

Type

White

Part Number
1SNA199420R2100
1SNA117600R0300
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173226R2700
1SNA163311R2200
1SNA173016R1000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
10
25
1

2.00
0.80
2.00
3.00
4.00
10.00
5.00
0.40
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with DR4/6...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

Type
DR4/6.PPart Number
1SNA160496R2600

Pkg

Weightpce(1 pce) g

50

10.00

1SNC161130S0201 - Rev. A

6

Type

DR4/6.P screw clamp terminal blocks
Miniblocks - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description–– Save space with compact over-all dimensions terminal block,–– For DIN 2 rail,–– Reliable electrical and mechanical contact with the rail.

Ordering details

1SNC161130F0014

Description
GroundColor
Screwless rail
connection

TypePart Number
1SNA160496R2600

DR4/6.P

10.00

IEC

UL

CSA

Rail

TH 15-5.5

22-12 AWG

28-10 AWG

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

Torque31 1.22"50

DR4/6.P

Mounting instructions

4 mm²
480 A

Rated cross section
Rated short-time withstand current (1s)

28 1.10"Weight(1 pce) g

Green-yellow

Main technical data
1 conductor
per clamp

Pkg
pce

12 AWG

10 AWGThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when apply) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

CE

RoHS

USR

US

cCSAusGost R6
6 mm 0.236 in spacing

Accessories
Description
1

3

2

4

1
2
3
4
5

End stops
6.5 mmEnd sections
1 mm
Lateral jumper bars 10 poles
Circuit separators 0.3 mm
Terminal block markers Blank card

Color
0.256 in
0.039 in
35 A
0.012 in

Grey
Grey
White
White

Type
BADRL
FEDR61
PC61-10SCDR61
RC65

Part Number
1SNA199420R2100
1SNA117600R0300
1SNA163311R2200
1SNA173016R1000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
25
10
25
1

2.00
0.80
5.00
0.40
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161050S0201 - Rev. A

5

Technical data valid for copper conductors only.

PAGE 119DR2.5/5.S screw clamp terminal blocks
Miniblocks - 5.08 mm 0.200 in spacing
2.5 mm²

Description–– Save space with compact over-all dimensions terminal block,–– Ease your disconnect operations with the disconnect plug.

Ordering details
Description

1SNC161307F0014

Miniblocks

Color
Disconnect
with 2 test sockets
DIA 2 mm 0.079 in

1SNA112098R1600

UL

CSA

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-2.5 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
38.5 1.12"

DR2.5/5.S1

Pkg

Weightpce(1 pce) g

100

6.00

Mounting instructions
IEC

DR2.5/5.S

3 A / 2.5 mm²
300 A
380 V
IP20

Rail

TH 15-5.5

Wire stripping
length

8.5 mm0.335 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

5.08 mm 0.200 in spacing

Accessories
Description
1

3

2

4

1
2
3
4

End stops
6.5 mm0.256 inEnd sections
1 mm
0.039 inShield connectors
Terminal block markers Blank card

Color
Grey
Grey
White

Type
BADRL
FEDR51
CBD5
RC55Part Number
1SNA199420R2100
1SNA117668R0200
1SNA167674R0200
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
25
25
1

2.00
1.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161132S0201 - Rev. A

6

Grey

Part Number

Main technical data
1 conductor
per clamp

27.5 1.08"

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDR4/8.SF screw clamp terminal blocks
Miniblocks - 8 mm 0.315 in spacing
Description

4 mm²–– Save space with compact over-all dimensions terminal block,–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not supplied with terminal blocks).

12 AWG

Ordering details

1SNC161140F0014

Description
Miniblocks

Color
Fuse

Grey

UL

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
41 1.61"

DR4/8.SF

1SNA110368R1200

Pkg

Weightpce(1 pce) g

50

14.00

Mounting instructions
IEC

DR4/8.SF

180°

Part Number

Main technical data
1 conductor
per clamp

59.5 2.34"

Type

6.3 A / 4 mm²
480 A
630 V
8000 V
IP20

CSA

Rail

TH 15-5.5

18 - 12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

6.3 A / 12 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

CSA

Gost R

8 mm 0.315 in spacing
6

Accessories
Description
2

3

4

5

6

7

8

1
2
3
4

5
6
7
8

End stops
End stops 0.256 in
End sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A
Fuses
0.5 A
3.15 A
1A
2A
5A
Assembly rods
2 poles
3 poles
4 poles
Neutral cartridges
Spring retaining rings
Terminal block markers Blank card

Grey
Grey

Type
BADRL
FEM8S
PC81-10
FU520

TGA8

White

CN5
ANT
RC810

Part Number
1SNA199420R2100
1SNA116951R1500
1SNA173523R1100
1SNA008288R1500
1SNA008289R1600
1SNA008290R1300
1SNA008291R0000
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA179371R1600
1SNA168675R1400
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
10
10
1

2.00
2.60
5.00

1.00
3.90
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
1SNC161127S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 121

DS2.5/5.2L spring terminal blocks
Miniblocks - 5 mm 0.197 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy mounting on DIN rail TH35,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

Ordering details
1SNC162040F0014

Description
Feed-through38 1.50"

32 1.26"

39.5 1.56"

33 1.30"

2 connections

Type
Grey
Blue

Part Number

DS2.5/5.2L
DS2.5/5.N.2L

1SNA290221R0400
1SNA290223R0600

Main technical data
1 conductor
per clamp

DS2.5/5.2L

Color

Pkg

Weightpce(1 pce) g

100
100

4.00
4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.12-4 mm²
0.12-2.5 mm²

26-12 AWG

0.5-1.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 15 A / 12 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

19 0.75"

Notes
6
/

5 mm 0.197 in spacing

Description
1

2

1
2

3

4

3

4

5.2 mm
10 mm
End sections
1.5 mm4 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 polesTerminal block markers Blank card
End stops

Color
0.205 in
0.394 in0.059 in
0.157 in
24 A

Dark grey
Grey
Orange

White

Type
BAZ1
BAM4
FED1.L
FED2.LBJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA291301R0200
1SNA291311R2300
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA230000R1200

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
20
50
50
50
20
20
1

5.30
14.00
1.40
1.90
1.00
0.70
0.80
0.90
1.20
2.90
1SNC162090S0201 - Rev. B

Accessories

DS2.5/10.4L spring terminal blocks
Miniblocks - 10 mm 0.394 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy mounting on DIN rail TH35,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

Ordering details
1SNC162070F0014

Description
Feed-throughColor
4 connections

Grey
Blue
Yellow

TypePart Number

DS2.5/10.4L
DS2.5/10.N.4L
DS2.5/10.4L.YL

1SNA290231R0600
1SNA290233R0000
1SNA290501R0000

Main technical data
1 conductor
per clamp

DS2.5/10.4L

32 1.26"

39.5 1.56"

Weight(1 pce) g

100
100
100

6.00
6.00
6.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

IEC

UL

CSA

0.12-4 mm²
0.12-2.5 mm²

26-12 AWG

0.5-1.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

38 1.50"
33 1.30"

Pkg
pce

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm² 15 A / 12 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
19 0.75"

10 mm 0.394 in spacingRoHS

USR CNR

Gost R

Notes

6/

Accessories
Description
1

2

1
2

4

3

4

0.205 in
0.394 in0.059 in
0.157 in
24 A

Dark grey
Grey
Orange

White

Type
BAZ1
BAM4
FED1.L
FED2.LBJDL10-2
BJDL10-3
BJDL10-4
BJDL10-5
RC55Part Number
1SNK900002R0000
1SNK900001R0000
1SNA291301R0200
1SNA291311R2300
1SNA291322R2600
1SNA291323R2700
1SNA291324R2000
1SNA291325R2100
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
20
50
50
20
20
1

5.30
14.00
1.40
1.90
1.00
1.00
2.00
2.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
1SNC162091S0201 - Rev. B

3

5.2 mm
10 mm
End sections
1.5 mm4 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 123DR2.5/5.2L spring terminal blocks
Miniblocks - 5 mm 0.197 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy mounting on DIN rail TH15,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

Ordering details
1SNC162083F0014

Description
Feed-through30 1.18"

33 1.30"

2 connections

Part Number

DR2.5/5.2L
DR2.5/5.N.2L

Grey
Blue

1SNA290201R1100
1SNA290203R1300

Pkg

Weightpce(1 pce) g

100
100

4.00
4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.12-4 mm²
0.12-2.5 mm²

26-12 AWG

0.5-1.5 mm²
A2

Rail

TH 15-5.5

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 15 A / 12 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

16.5 0.65"

5 mm 0.197 in spacing

USR CNR

Gost R/

Accessories
Description
1

2

1
2
3

3

4

4

Color

6.5 mm
1.5 mm4 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 polesTerminal block markers Blank card
End stops
End sections

0.256 in0.059 in
0.157 in
24 A

Grey
Grey
Orange

White

Type
BADRL
FED1.L
FED2.LBJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
RC55

Part Number
1SNA199420R2100
1SNA291301R0200
1SNA291311R2300
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
20
20
50
50
50
20
20
1

2.00
1.40
1.90
1.00
0.70
0.80
0.90
1.20
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground spring terminal blocks
Description
GroundColor
Profile aligned with DR2.5/...L

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeDR2.5/10.P.4L

Part Number
1SNA290219R1200

Pkg

Weightpce(1 pce) g

100

7.00

1SNC162092S0201 - Rev. B

6

Type

Main technical data
1 conductor
per clamp

DR2.5/5.2L

Color

DR2.5/10.4L spring terminal blocks
Miniblocks - 10 mm 0.394 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy mounting on DIN rail TH15,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

Ordering details
1SNC162063F0014

Description
Feed-through30 1.18"

33 1.30"

4 connections

Type

Part Number

DR2.5/10.4L
DR2.5/10.N.4L

Grey
Blue

1SNA290211R0200
1SNA290213R0400

Main technical data
1 conductor
per clamp

DR2.5/10.4L

Color

Pkg

Weightpce(1 pce) g

100
100

6.00
6.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.12-4 mm²
0.12-2.5 mm²

26-12 AWG

0.5-1.5 mm²
A2

Rail

TH 15-5.5

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 15 A / 12 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

16.5 0.65"

6/

10 mm 0.394 in spacing

Accessories
Description
2

1
2
3

3

4
4

6.5 mm
1.5 mm4 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
Terminal block markers Blank card
End stops
End sections

0.256 in0.059 in
0.157 in
24 A

Grey
Grey
Orange

White

Type
BADRL
FED1.L
FED2.LBJDL10-2
BJDL10-3
BJDL10-4
BJDL10-5
RC55Part Number
1SNA199420R2100
1SNA291301R0200
1SNA291311R2300
1SNA291322R2600
1SNA291323R2700
1SNA291324R2000
1SNA291325R2100
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
20
20
50
50
20
20
1

2.00
1.40
1.90
1.00
1.00
2.00
2.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground spring terminal blocks
Description
GroundColor
Profile aligned with DR2.5/...L

Green-yellow

TypeDR2.5/10.P.4L

Part Number
1SNA290219R1200

Pkg

Weightpce(1 pce) g

100

7.00

Technical data valid for copper conductors only.

PAGE 125

1SNC162093S0201 - Rev. B

1

Color

DR2.5/10.P.4L spring terminal blocks
Miniblocks - 10 mm 0.394 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy mounting on DIN rail TH15,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

Ordering details
1SNC162071F0014

Description
GroundColor
Screwless rail connection Green-yellow

1 conductor
per clamp
DR2.5/10.P.4L

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated cross section
Rated short-time withstand current (1s)Protection
30 1.18"

DR2.5/10.P.4L

1SNA290219R1200

Pkg

Weightpce(1 pce) g

100

7.00

Mounting instructions
Rail

TH 15-5.5

0.12-4 mm²
0.12-2.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.5-1.5 mm²
A2

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

2.5 mm²
300 A
IP20

UL

CSA

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

16.5 0.65"

Gost R/

10 mm 0.394 in spacing

Accessories
1

3

Description

2
1
2
3

End stops
6.5 mm0.256 inEnd sections
1.5 mm
0.059 inTerminal block markers Blank card

Color
Grey
Grey
White

Type
BADRL
FED1.L
RC55

Part Number
1SNA199420R2100
1SNA291301R0200
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
20
1

2.00
1.40
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC162094S0201 - Rev. B

6

Part Number

Main technical dataIEC33.5 1.32"

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDB2.5/5.2L spring terminal blocks
Miniblocks - 5 mm 0.197 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy base mounting thanks to the usage of flanges,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

1SNC162112F0014

Ordering details
Description
Feed-throughColor
2 connections

Type

Part Number

DB2.5/5.2L
DB2.5/5.N.2L

Grey
Blue

1SNA290241R1000
1SNA290243R1200

Main technical data

Pkg

Weightpce(1 pce) g

100
100

4.00
4.00

Mounting instructions
IEC

UL

CSA

0.12-4 mm²
0.12-2.5 mm²

26-12 AWG

Rail

DB2.5/5.2L

1 conductor
per clamp

24.5 0.97"

33 1.30"5 mm 0.197 in spacing

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.5-1.5 mm²
A2

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 15 A / 12 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Notes/

6

L = (N blocks x 5.05) + (N blocks x 10)
A: 2 holes DIA 3.2 mm for 3 mm screw with cylindrical head (not supplied)A

Accessories
Description

3

2

1
2
3

4
4

End section kits
End sections
Jumper bars

4 mm
0.157 in
2 poles
24 A
3 poles
4 poles
5 poles
10 polesTerminal block markers Blank card

Grey
Grey
OrangeWhite

Type
FEDB.L
FED2.LBJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
RC55

Part Number
1SNA290281R0100
1SNA291311R2300
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

20
20
50
50
50
20
20
1

3.00
1.90
1.00
0.70
0.80
0.90
1.20
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC162095S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

PAGE 127

DH2.5/5.2L spring terminal blocks
Miniblocks - 5 mm 0.197 in spacing
2.5 mm²
12 AWG

Description–– Save space with compact terminal blocks,–– Easy base mounting thanks to snap in mounting foot,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

Ordering details
1SNC162114F0014

Description

Color
2 connections

Feed-through4.5 0.18"

24.5 0.97"

33 1.30"

DH2.5/5.2L

Grey

1SNA290261R1400

Pkg

Weightpce(1 pce) g

100

4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.12-4 mm²
0.12-2.5 mm²

26-12 AWG

0.5-1.5 mm²
A2

RailWire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 15 A / 12 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

16.5 0.65"

5 mm 0.197 in spacing

Part Number

Main technical data
1 conductor
per clamp

DH2.5/5.2L

Type

RoHS

USR CNR

Gost R

Notes
For 10 mm blocks, mount a DH block every 4 blocks.
For 5 mm blocks, mount a DH block every 8 blocks.

//

N blocks = 8 blocks max with 5 mm spacing
N blocks = 4 blocks max with 10 mm spacing6

L = (N blocks x 5.05) + (N blocks x 10)
Panel thickness: 0.6 to 1.2 mm 0.024 to 0.047 inØ 3.2
2.5 / 5

Ø 3.2
5.05 / 10

2.5 / 5

2.5 / 5

Accessories
Description
1

2

1
2

3
3

1.5 mm
0.059 in
4 mm
0.157 inJumper bars
2 poles
24 A
3 poles
4 poles
5 poles
10 polesTerminal block markers Blank card
End sections

Color
Grey
OrangeWhite

Type
FED1.L
FED2.LBJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
RC55

Part Number
1SNA291301R0200
1SNA291311R2300
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

20
20
50
50
50
20
20
1

1.40
1.90
1.00
0.70
0.80
0.90
1.20
2.90

1SNC162099S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDS2.5/5.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 5 mm 0.197 in spacing
1 mm²
18 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163080F0014

Ordering details
Description

Color

Type

Part Number

pceFeed-throughWith rib
Without rib for TB
assembly extremity

DS2.5/5.ADO
DSE2.5/5.ADO

Grey
Grey

1SNA399514R2300
1SNA399518R0700

Main technical data
DS2.5/5.ADO

Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

43 1.69"

35.5 1.39"

42.3 1.66"
31 1.22"

5

DS

0.20"

20.6 0.81"100
20Weight(1 pce) g
4.00
4.00

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

24-18 AWG

Wire stripping
length

9.5 mm0.37 in24-12 AWG

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.in

IEC

UL

0.2-1 mm²0.22-1 mm²
0.2-4 mm²0.22-2.5 mm²

CSA

A3
13.5 A / 1 mm² 10 A / 18 AWG
120 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

DSE

5 mm 0.197 in spacing

Pkg

USR CNR

Gost R

6

Notes
DSE...

5-6-8

FEAD1

FEAD5

DS...

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DSE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

Description

2
1

3

4

5

6

2
3
4

7

8

5
6
7
8

10 mm 0.394 in
5.2 mm 0.205 in
End sections
2.5 mm 0.098 in
Jumper bars
2 poles 13.5 A
3 poles
10 poles
Lateral jumper bars 2 poles 30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color
Dark grey
Grey
Orange

Grey

Grey

White

Type
BAM4
BAZ1
FEAD1
BJADO5-2
BJADO5-3
BJADO5-10
PC5-2
PC5-10
EIP
FEAD5
OUPAD
OUMAD
RC55

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199421R1600
1SNA205955R0300
1SNA205956R0400
1SNA205963R0300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
10
10
10
20
1
1
1

14.00
5.30
1.30
1.00
1.00
5.00
1.80
6.00
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 129

1SNC163027S0201 - Rev. B

Accessories
1DS4/6.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163080F0014

Ordering details
Description

Color

Type

Part Number

Feed-throughWith rib
Without rib for TB
assembly extremity

DS4/6.ADO
DSE4/6.ADO

Grey
Grey

1SNA299489R0700
1SNA299556R0100

Main technical dataDS4/6.ADO

Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

43 1.69"

35.5 1.39"

42.3 1.66"
31 1.22"6DS0.238"

20.6 0.81"

RoHS

6 mm 0.236 in spacing

100
20

Weight(1 pce) g
5.00
5.00

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

22-16 AWG

Wire stripping
length

9.5 mm0.37 in22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC

UL

0.28-1.5 mm²
0.34-1.5 mm²
0.2-4 mm²0.22-4 mm²CSA

A417.5 A / 1.5 mm² 20 A / 16 AWG
180 A
800 V
600 V
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

DSE

6

Pkg
pce

USR CNR

Gost R

Notes
DSE...

5-6-8

FEAD1

FEAD5

DS...

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DSE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

1

Description

2
1

3

4

2
3
4

5

7

6

8

5
6
7
8

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.5 mm
0.098 inJumper bars
2 poles17.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block Markers Blank card
End stops

Color
Dark grey
Grey
Orange

Grey

Grey

White

Type
BAM4
BAZ1
FEAD1
BJADO6-2
BJADO6-3
BJADO6-10
PC6-2
PC6-3
PC6-4
PC6-10
EIP
FEAD5
OUPAD
OUMAD
RC65

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199421R1600
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
10
10
10
10
10
20
1
1
1

14.00
5.30
1.30
1.00
1.00
6.00
2.00
2.00
1.00
8.00
1.80
205.0029.00
3.60

1SNC163028S0201 - Rev. A

Accessories

DS4/8.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163080F0014

Ordering details

DS4/8.ADO

Description

Color

Type

Part Number

Grey

DS4/8.ADO

1SNA299493R2300

100

Weight(1 pce) g
7.00

Grey

DSE4/8.ADO

1SNA299557R0200

20

7.00

pce

Feed-throughWith rib and 2 notches forwire size 1-2.5 mm²(16-14 AWG)
Without rib for TB assembly
extremity and 2 notches forwire size 1-2.5 mm²(16-14 AWG)

Main technical data

35.5 1.39"

43 1.69"8DSE

8 mm 0.315 in spacing

0.315"

20.6 0.81"
DS

Rigid: Solid/Stranded
Flexible without ferrule

ADO

42.3 1.66"
31 1.22"

Pkg

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

16-14 AWG

Wire stripping
length

9.5 mm0.37 in22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC

UL

1-2.5 mm²
1-2.5 mm²
0.2-4 mm²0.22-4 mm²CSA

A424 A / 2.5 mm² 25 A / 14 AWG
300 A
1000 V
600 V
IP20NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

6

Gost R

Notes
DSE...

5-6-8

FEAD1

FEAD5

DS...

2

Accessories
Description
1

3

5

4

6

5-6-8

2
3
4
5
6

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.5 mm
0.098 inJumper bars
1 poles
24 A
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey
Grey
Grey

Type
BAM4
BAZ1
FEAD1
AD2.5
FEAD5
OUPAD
OUMAD
RCAL85

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199421R1600
1SNA114205R2000
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
50
20
50
20
1
1
1

14.00
5.30
1.30
1.60
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with DS4/8.ADO

Green-yellow

Type
DS4/8.P.ADO

Part Number
1SNA199527R1000

Pkg

Weightpce(1 pce) g

100

8.00

Technical data valid for copper conductors only.

PAGE 131

1SNC163029S0201 - Rev. A

1–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DSE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

DS4/8.P.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 8 mm 0.315 in spacing

1SNC163127F0014

2.5 mm²

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Part Number

With 2 notches for wire size
1-2.5 mm² (16-14 AWG)

Green-yellow

DS4/8.P.ADO

IEC

UL

1SNA199527R1000

Main technical data

DS4/8.P.ADO

ADO
49 1.92"
31 1.22"

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
Rated short-time withstand current (1s)Protection

43 1.69"

35 1.37"

Screw clamp

80.315"

25 0.98"

Pkg
pce

Ground100

Weight(1 pce) g
8.00

Mounting instructions
Rail

TH 35-7.5,
TH 35-15

1-2.5 mm²

Wire stripping
length

9.5 mm0.37 in

0.2-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4 - 7.1 lb.in

A4
2.5 mm²
300 A
IP20

CSA

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

RoHS

Gost R

Accessories
Description
1

2

1
2

3

3

10 mm
0.394 in
5.2 mm0.205 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color
Dark grey

Type
BAM4
BAZ1
OUPAD
OUMAD
RCAL85

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
50
1
1
1

14.00
5.30
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163030S0201 - Rev. A

6

Type

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDR2.5/5.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 5 mm 0.197 in spacing
1 mm²
18 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163073F0014

Ordering details
Description

Color

Type

Part Number

pceFeed-throughWith rib
Without rib for TB
assembly extremity

DR2.5/5.ADO
DRE2.5/5.ADO

Grey
Grey

1SNA399509R1700
1SNA399513R2200

Main technical data
DR2.5/5.ADO

Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

33.5 1.32"

31 1.22"

5

DR

Mounting instructions
Rail

TH 15-5.5

24-18 AWG

Wire stripping
length

9.5 mm
0.374 in24-12 AWG

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.in

IEC

UL

0.2-1 mm²0.22-1 mm²
0.2-4 mm²0.22-2.5 mm²

CSA

A3
13.5 A / 1 mm² 10 A / 18 AWG
120 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

DRE

5 mm 0.197 in spacing

100
20

Weight(1 pce) g
4.00
4.00

0.20"

15.5 0.61"

Pkg

USR CNR

Gost R

6

Notes
DRE...

5-6-8

FEAD1

FEAD5

DR...

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DRE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

3

Description

2

4

1
2
3
4

5

7

6

8

5
6
7
8

6.5 mm0.256 in
2.5 mm
0.098 in
2 poles13.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Grey
Grey
Orange

Grey

Grey

White

Type
BADRL
FEAD1
BJADO5-2
BJADO5-3
BJADO5-10
PC5-2
PC5-10
EIP
FEAD5
OUPAD
OUMAD
RC55

Part Number
1SNA199420R2100
1SNA199421R1600
1SNA205955R0300
1SNA205956R0400
1SNA205963R0300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
20
20
20
10
10
10
10
20
1
1
1

2.00
1.30
1.00
1.00
5.00
1.80
6.00
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 133

1SNC163031S0201 - Rev. A

Accessories
1DR4/6.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163073F0014

Ordering details
Description

Color

Type

Part Number

Feed-throughWith rib
Without rib for TB
assembly extremity

DR4/6.ADO
DRE4/6.ADO

Grey
Grey

1SNA199275R0300
1SNA299552R0500

Main technical data
DR4/6.ADO

Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

33.5 1.32"

31 1.22"

6

DR

RoHS

DRE

6
6 mm 0.236 in spacing

100
20

Weight(1 pce) g
5.00
5.00

Mounting instructions
Rail

TH 15-5.5

22-16 AWG

Wire stripping
length

9.5 mm
0.374 in22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC

UL

0.28-1.5 mm²
0.34-1.5 mm²
0.2-4 mm²0.22-4 mm²CSA

A417.5 A / 1.5 mm² 20 A / 16 AWG
180 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

0.24"

15.5 0.61"

Pkg
pce

USR CNR

Gost R

Notes
DRE...

5-6-8

FEAD1

FEAD5

DR...

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DRE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

Description
1

3

5

7

2

4

6

8

1
2
3
4

5
6
7
8

6.5 mm0.256 in
2.5 mm
0.098 in
2 poles17.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Grey
Grey
Orange

Grey

Grey

White

Type
BADRL
FEAD1
BJADO6-2
BJADO6-3
BJADO6-10
PC6-2
PC6-3
PC6-4
PC6-10
EIP
FEAD5
OUPAD
OUMAD
RC65

Part Number
1SNA199420R2100
1SNA199421R1600
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
20
20
20
10
10
10
10
10
10
20
1
1
1

2.00
1.30
1.00
1.00
6.00
2.00
2.00
1.00
8.00
1.80
205.0029.00
3.60

1SNC163032S0201 - Rev. A

Accessories

DR4/8.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

1SNC163090F0014

Ordering details
Description

Color

Type

Part Number

pceFeed-throughWith rib and 2 notches forwire size 1-2.5 mm²(16-14 AWG)

Grey

DR4/8.ADO

1SNA199279R1700

Main technical data
DR4/8.ADO

Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

33.5 1.32"

31 1.22"8DR0.315"

15.5 0.61"

Pkg
100

Weight(1 pce) g
7.00

Mounting instructions
Rail

TH 15-5.5

16-14 AWG

Wire stripping
length

9.5 mm
0.374 in22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

IEC

UL

1-2.5 mm²
1-2.5 mm²
0.2-4 mm²0.22-4 mm²CSA

A424 A / 2.5 mm² 25 A / 14 AWG
300 A
1000 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

DRE

USR CNR

Gost R

6Notes
8 mm 0.315 in spacing
DRE...

5-6-8

FEAD1

FEAD5

DR...

3

5

2

4

6

5-6-8

Accessories
Description
1
2
3
4
5
6

Color

6.5 mm0.256 in
2.5 mm
0.098 in
1 poles
24 A
5 mm
0.197 inSemi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars
Circuit separators
Tools

Grey
Grey
Grey
Grey

Type
BADRL
FEAD1
AD2.5
FEAD5
OUPAD
OUMAD
RCAL85

Part Number
1SNA199420R2100
1SNA199421R1600
1SNA114205R2000
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
20
50
20
1
1
1

2.00
1.30
1.60
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with DR4/8.ADO

Green-yellow

Type
DR4/8.P.ADO

Part Number
1SNA299632R0500

Pkg

Weightpce(1 pce) g

100

8.00

Technical data valid for copper conductors only.

PAGE 135

1SNC163033S0201 - Rev. A

1–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DRE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

DR4/8.P.ADO IDC Terminal Blocks
Miniblocks ADO - screw clamp - 8 mm 0.315 in Spacing

1SNC163144F0014

2.5 mm²

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Up to 2 wires per connection in the ADO System® connection.

Ordering Details
Description

Color

Type

Part Number

GroundGround with 2 notches
for wire size 1-2.5 mm²(16-14 AWG)

Green-Yellow

DR4/8.P.ADO

IEC

UL

1SNA299632R0500

Main Technical Data
DR4/8.P.ADO

ADO
32 1.26"
31 1.22"

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
Rated short-time withstand current (1s)Protection
Screw clamp

33 1.29"

Pkg
pce

100

Weight(1 pce) g
8.00

Mounting Instructions
Rail

TH 15-5.5

1-2.5 mm²
1-2.5 mm²

Wire stripping
length

9.5 mm
0.374 in

0.2-4 mm²0.22-4 mm²

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

CSA

A4
2.5 mm²
300 A
NEMA

8

0.315"

15.5 0.61"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6RoHS

8 mm 0.315 in Spacing

Gost R

Accessories
Description
1

3

2

4

1
2
3
4

6.5 mm 0.256 in
2.5 mm 0.098 in
Semi automatic tool
Hand tool
Terminal block markers Blank card

End Stops
End Sections
Tools

Color
Grey
Grey

Type
BADRL
FEAD1
OUPAD
OUMAD
RCAL85

Part Number
1SNA199420R2100
1SNA199421R1600
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
20
1
1
1

2.00
1.30
205.0029.00
2.90

1SNC163034S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDB2.5/5.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 5 mm 0.197 in spacing
1 mm²

1SNC163049F0014

18 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Easy base mounting thanks to the usage of flanges,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

pceFeed-throughDB2.5/5.ADO

Grey

1SNA399519R0000

Main technical data

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

28 1.10"31 1.22"100

Weight(1 pce) g
4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

DB2.5/5.ADO

Pkg

CSA

Rail

IEC

UL

0.2-1 mm²0.22-1 mm²

24-18 AWG

Wire stripping
length

9.5 mm
0.374 in

0.2-4 mm²0.22-2.5 mm²

24-12 AWG

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.in

A3
13.5 A / 1 mm² 10 A / 18 AWG
120 A
800 V
600 V
8000 V
IP20
NEMA 150.197"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost RNotes
5 mm 0.197 in spacing

6
A: 2 holes DIA 3.2 mm for 3 mm screw max. with cylindrical head (not supplied).

/

L = (N blocks x 6) + (N blocks x 8)
Plate thickness 0.6 to 1.2 mm

BIntermediate mounting of DH blocks every 2 blocks (spacing 8 mm) or 3 blocks(spacing 6 mm)

A

Accessories
Description
1

3

5

2

4

6

1
2
3
4
5
6
7

End section kits
Jumper bars

2 poles13.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Grey
Orange

Grey

Grey

White

Type
FEAD3
BJADO5-2
BJADO5-3
BJADO5-10
PC5-2
PC5-10
EIP
FEAD5
OUPAD
OUMAD
RC55

Part Number
1SNA199437R1600
1SNA205955R0300
1SNA205956R0400
1SNA205963R0300
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

20
20
20
10
10
10
10
20
1
1
1

3.00
1.00
1.00
5.00
1.80
6.00
1.80
205.0029.00
2.90
1SNC163035S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

Technical data valid for copper conductors only.

PAGE 137

DB4/6.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²

1SNC163049F0014

16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Easy base mounting thanks to the usage of flanges,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

Feed-throughDB4/6.ADO

Grey

1SNA299505R0700

Main technical data

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

28 1.10"31 1.22"100

Weight(1 pce) g
5.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

DB4/6.ADO

Pkg
pce

CSA

Rail

IEC

UL

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG
22-16 AWG

Wire stripping
length

9.5 mm
0.374 in

0.2-4 mm²0.22-4 mm²22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
17.5 A / 1.5 mm² 20 A / 16 AWG
180 A
800 V
600 V
8000 V
IP20
NEMA 16

6
6 mm 0.236 in spacing

0.238"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

USR CNRUS

cCSAusGost R

Notes
A: 2 holes DIA 3.2 mm for 3 mm screw max. with cylindrical head (not supplied)/L = (N blocks x 6) + (N blocks x 8)
Plate thickness 0.6 to 1.2 mm

BIntermediate mounting of DH blocks every 2 blocks (spacing 8 mm) or 3 blocks(spacing 6 mm)

A

Description
1

2

3

4

5

6

1
2
3

4
5
6
7

7

End section kits
Jumper bars

2 poles17.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Grey
Orange

Grey

Grey

White

Type
FEAD3
BJADO6-2
BJADO6-3
BJADO6-10
PC6-2
PC6-3
PC6-4
PC6-10
EIP
FEAD5
OUPAD
OUMAD
RC65

Part Number
1SNA199437R1600
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

20
20
20
10
10
10
10
10
10
20
1
1
1

3.00
1.00
1.00
6.00
2.00
2.00
1.00
8.00
1.80
205.0029.00
3.60

1SNC163036S0201 - Rev. A

Accessories

DB4/8.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 8 mm 0.315 in spacing
2.5 mm²

1SNC163059F0014

14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allows installators to connect on standard screw
clamp,–– Easy base mounting thanks to the usage of flanges,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

pceWith 2 notches for wire
size 1-2.5 mm2(16-14 AWG)

Feed-throughGrey

DB4/8.ADO

1SNA299509R1300

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule

ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

28 1.10"80.315"

CSA

Rail

IEC

UL

1-2.5 mm²
1-2.5 mm²

16-14 AWG

Wire stripping
length

9.5 mm
0.374 in

0.2-4 mm²0.22-4 mm²22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
24 A / 2.5 mm² 25 A / 14 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

8 mm 0.315 in spacing

100

Weight(1 pce) g
7.00

Mounting instructions

DB4/8.ADO

31 1.22"Pkg

USR CNR

Gost R

6

Notes
A: 2 holes DIA 3.2 mm for 3 mm screw max. with cylindrical head (not supplied)/L = (N blocks x 6) + (N blocks x 8)
Plate thickness 0.6 to 1.2 mm

BIntermediate mounting of DH blocks every 2 blocks (spacing 8 mm) or 3 blocks(spacing 6 mm)

A

Accessories
1

3

Description

2

4

1
2
3
4
5

End section kits
Jumper bars
1 poles
24 A
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Grey
Grey
Grey

Type
FEAD3
AD2.5
FEAD5
OUPAD
OUMAD
RCAL85

Part Number
1SNA199437R1600
1SNA114205R2000
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

20
50
20
1
1
1

3.00
1.60
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163037S0201 - Rev. A

5

Technical data valid for copper conductors only.

PAGE 139

DH4/6.ADO IDC terminal blocks
Miniblocks ADO - screw clamp - 6 mm 0.236 in spacing
1.5 mm²

1SNC163048F0014

16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– This solution brings all the benefits of the ADO System® and allow installators to connect on standard screw
clamp,–– Easy base mounting thanks to snap in mounting foot,–– Up to 2 wires per connection in the ADO System® connection.

Ordering details
Description

Color

Type

Part Number

Feed-throughDH4/6.ADO

Grey

1SNA299521R2600

Main technical data

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
Screw clamp

28 1.10"31 1.22"100

Weight(1 pce) g
5.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

DH4/6.ADO

Pkg
pce

CSA

Rail

IEC

UL

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG

Wire stripping
length

9.5 mm
0.374 in

0.2-4 mm²0.22-4 mm²22-10 AWG

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

A4
17.5 A / 1.5 mm² 20 A / 16 AWG
180 A
800 V
600 V
8000 V
IP20
NEMA 16

6
6 mm 0.236 in spacing

0.238"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Notes//

L = (N blocks x 6) + (N blocks x 8)
N blocks = 3 blocks max. with 6 mm spacing
2 blocks max. with 8 mm spacing
Plate thickness 0.6 to 1.2 mm

3/4

6/8

3/4

3/4

Description
1

2

3

4

5

6

1
2
3

4
5
6
7

7

End section
Jumper bars

2 poles17.5 A
3 poles
10 poles
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Grey
Orange

Grey

Grey

White

Type
FEAD1
BJADO6-2
BJADO6-3
BJADO6-10
PC6-2
PC6-3
PC6-4
PC6-10
EIP
FEAD5
OUPAD
OUMAD
RC65

Part Number
1SNA199421R1600
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA199433R1200
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

20
20
20
10
10
10
10
10
10
20
1
1
1

1.30
1.00
1.00
6.00
2.00
2.00
1.00
8.00
1.80
205.0029.00
3.60

1SNC163038S0201 - Rev. A

Accessories

DS1.5/6.ADO IDC terminal blocks
Miniblocks ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163096F0014

Description

Color

Type

Part Number

pceFeed-throughWith rib
Without rib for TB
assembly extremity

DS1.5/6.ADO
DSE1.5/6.ADO

Grey
Grey

1SNA299497R2700
1SNA299558R1300

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule

ADO

DS1.5/6.ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG

43 1.69"

35.5 1.39"

Rail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

17.5 A / 1.5 mm² 20 A / 16 AWG
180 A
1000 V
600 V
IP20TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
6

0.238"

20.6 0.81"
DS

100
20

Weight(1 pce) g
4.00
4.00

Mounting instructions
IEC

Screw clamp

42.3 1.66"
31 1.22"

Pkg

RoHS

USR CNR

Gost R

DSE

Notes

6

6 mm 0.236 in spacing
DSE...

5-6-8

FEAD2

FEAD6

DS...

–– End section FEAD2 to be mounted directly on the open part of the terminal
block.
–– End terminal block DSE has to be mounted at the end of the terminal
blocks assembly: It reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– Separator FEAD6 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

Accessories
Description
1

2

1
2
3

3

4
4
5
6

6

Dark grey
Grey
Orange

Grey

White

Type
BAM4
BAZ1
FEAD2
BJADO6-2
BJADO6-3
BJADO6-10
FEAD6
OUPAD
OUMAD
RC65

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199423R1000
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
20
1
1
1

14.00
5.30
1.30
1.00
1.00
6.00
1.80
205.0029.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
1SNC163063S0201 Rev. A

5

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.5 mm
0.098 inJumper bars
2 poles17.5 A
3 poles
10 polesCircuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 141

DS2.5/8.ADO IDC terminal blocks
Miniblocks ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163096F0014

Description

Color

Type

Part Number

Grey

DS2.5/8.ADO

1SNA299501R0300

100

Weight(1 pce) g
6.00

Feed-throughWith rib and 2 notches forwire size 1-2.5 mm²(16-14 AWG)
Without rib for TB assembly
extremity and 2 notches
for wire size 1-2.5 mm²(16-14 AWG)

Grey

DSE2.5/8.ADO

1SNA299559R1400

20

6.00

Main technical data

DS2.5/8.ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

1-2.5 mm²
1-2.5 mm²

16-14 AWG

35.5 1.39"

43 1.69"80.315"

Rail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

20.6 0.81"
DS

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO
42.3 1.66"
31 1.22"Pkg
pce

24 A / 2.5 mm² 25 A / 14 AWG
300 A
1000 V
600 V
IP20TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

DSE

6

C

8 mm 0.315 in spacing

US

cCSAusRoHS

Gost R

Notes
DSE...

5-6-8

FEAD2

FEAD6

DS...

–– End section FEAD2 to be mounted directly on the open part of the terminal
block.
–– End terminal block DSE has to be mounted at the end of the terminal
blocks assembly: It reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– Separator FEAD6 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

Accessories
Description

2
1

3

4

2
3
4
5

5

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.5 mm
0.098 inCircuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Dark grey
Grey
Grey

Type
BAM4
BAZ1
FEAD2
FEAD6
OUPAD
OUMAD
RCAL85

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199423R1000
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
50
20
20
1
1
1

14.00
5.30
1.30
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with DS2.5/8.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeDS2.5/8.P.ADO

Part Number
1SNA199528R2100

Pkg

Weightpce(1 pce) g

100

10.00

1SNC163064S0201 - Rev. A

1DS2.5/8.P.ADO IDC terminal blocks
Miniblocks ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²

1SNC163140F0014

14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

pce

GroundWith 2 notches for wire
size 1-2.5 mm2(16-14 AWG)

Green-yellow

DS2.5/8.P.ADO

IEC

UL

1-2.5 mm²
1-2.5 mm²

16-14 AWG

1SNA199528R2100

Main technical data

DS2.5/8.P.ADO

ADO
49 1.92"
31 1.22"43 1.69"

35 1.37"80.315"

100

Weight(1 pce) g
10.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
2.5 mm²
Rated short-time withstand current (1s) 300 A
Protection
IP20

CSA

Rail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

25 0.98"

Pkg

14 AWG
TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

C

RoHS

US

cCSAusGost R

6

Accessories
Description
1

2

1
2
3

4

4

Dark grey
Grey

Type
BAM4
BAZ1
FEAD2
OUPAD
OUMAD
RCAL85

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199423R1000
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
50
20
1
1
1

14.00
5.30
1.30
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163065S0201 - Rev. A

3

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.5 mm
0.098 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 143

DR1/5.ADO IDC terminal blocks
Miniblocks ADO-ADO - 5 mm 0.197 in spacing
1 mm²
18 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163100F0014

Description

Color

Type

Part Number

Feed-throughWith rib
Without rib for TB
assembly extremity

Grey
Grey

DR1/5.ADO
DRE1/5.ADO

1SNA399491R2500
1SNA399495R2100

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule

ADO

DR1/5.ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

0.2-1 mm²0.22-1 mm²

24-18 AWG

33.5 1.32"
5

DR

Rail

TH 15-5.5

Wire stripping
lengthTool

13.5 A / 1 mm² 10 A / 18 AWG
120 A
1000 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

0.197"

15.5 0.61"

100
20Weight(1 pce) g
3.00
3.00

Mounting instructions
IEC

Screw clamp

31 1.22"

Pkg
pce

RoHS

USR CNR

Gost R

DRE

Notes

6
5 mm 0.197 in spacing

DRE...

5-6-8

FEAD2

FEAD6

DR...

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DRE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

Accessories
Description
1

3

4

6

1
2
3
4
5
6

6.5 mm0.256 in
2.5 mm
0.098 in
2 poles13.5 A
3 poles
10 polesCircuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Grey
Grey
Orange

Grey

White

Type
BADRL
FEAD2
BJADO5-2
BJADO5-3
BJADO5-10
FEAD6
OUPAD
OUMAD
RC55

Part Number
1SNA199420R2100
1SNA199423R1000
1SNA205955R0300
1SNA205956R0400
1SNA205963R0300
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
20
20
20
10
20
1
1
1

2.00
1.30
1.00
1.00
5.00
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163066S0201 - Rev. A

5

2

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDR1.5/6.ADO IDC terminal blocks
Miniblocks ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163044F0014

Description

Color

Type

Part Number

pceFeed-throughWith rib
Without rib for TB assembly extremity

DR1.5/6.ADO
DRE1.5/6.ADO

Grey
Grey

1SNA199283R2400
1SNA299554R0700

Main technical data

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG
22-16 AWG

33.5 1.32"
6DR

TH 15-5.5

Tool

17.5 A / 1.5 mm² 20 A / 16 AWG
180 A
1000 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

0.238"

15.5 0.61"

Rail
Wire stripping
lengthScrew clamp

31 1.22"100
20Weight(1 pce) g
4.00
4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

DR1.5/6.ADO

Pkg

C

RoHS

US

cCSAusGost R

DRE

Notes

6

6 mm 0.236 in spacing
DRE...

5-6-8

FEAD2

FEAD6

DR...

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DRE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

5-6-8

Accessories
Description

3

5

2

4

6

1
2
3
4
5
6

6.5 mm0.256 in
2.5 mm
0.098 in
2 poles17.5 A
3 poles
10 polesCircuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Grey
Grey
Orange

Grey

White

Type
BADRL
FEAD2
BJADO6-2
BJADO6-3
BJADO6-10
FEAD6
OUPAD
OUMAD
RC65

Part Number
1SNA199420R2100
1SNA199423R1000
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
20
20
20
10
20
1
1
1

2.00
1.30
1.00
1.00
6.00
1.80
205.0029.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163067S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 145

DR2.5/8.ADO IDC terminal blocks
Miniblocks ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163089F0014

Description

DR2.5/8.ADO

Color

Type

Part Number

Grey

DR2.5/8.ADO

1SNA199287R2000

100

Weight(1 pce) g
6.00

Feed-throughWith rib and 2 notches
for wire size
1-2.5 mm2 (16-14 AWG)
Without rib for TB
assembly extremityand 2 notches for wire
size 1-2.5 mm2(16-14 AWG)

Grey

DRE2.5/8.ADO

1SNA299555R0000

20

6.00

Main technical data

33.5 1.32"
80.315"

DR

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

1-2.5 mm²
1-2.5 mm²

16-14 AWG
16-14 AWGRail

TH 15-5.5

Wire stripping
lengthTool

Screw clamp

15.5 0.61"

DRE

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

31 1.22"Pkg
pce

24 A / 2.5 mm² 25 A / 14 AWG
8000 A
1000 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6
8 mm 0.315 in spacing

CUS

cCSAusRoHS

Gost R

Notes
DRE...

5-6-8

FEAD2

FEAD6

DR...

5-6-8

–– End section FEAD1 to be mounted directly on the open part of the terminal
block.
–– End terminal block DRE has to be mounted at the end of the terminal
blocks assembly: it reduces its size, because it suppresses the insulationrib (- 4 mm).
–– Nota: This terminal block cannot be accidently located anywhere else into
the terminal block assembly (without locking holes)–– 
Separator FEAD5 which snaps on the terminal blocks, separates andmakes visible the different parts of the terminal blocks assembly.

Accessories

3

Description

2

4

1
2
3
4
5

5

Color

6.5 mm0.256 in
2.5 mm
0.098 in
5 mm
0.197 inSemi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Circuit separators
Tools

Grey
Grey
Grey

Type
BADRL
FEAD2
FEAD6
OUPAD
OUMAD
RCAL85

Part Number
1SNA199420R2100
1SNA199423R1000
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
20
20
1
1
1

2.00
1.30
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground IDC terminal blocks
Description
GroundColor
Profile aligned with DR2.5/8.ADO

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSGreen-yellow

TypeDR2.5/8.P.ADO

Part Number
1SNA299633R0600

Pkg

Weightpce(1 pce) g

100

8.00

1SNC163068S0201 - Rev. A

1DR2.5/8.P.ADO IDC terminal blocks
Miniblocks ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²

1SNC163141F0014

14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– Protect your installation in the event of a short-circuit thanks to our screwless rail contact non operator
dependent,–– Secure mounting or removal from the rail,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Up to 2 wires per connection.

Ordering details
Description

Color

Type

Part Number

pce

GroundWith 2 notches for wire
size 1-2.5 mm2(16-14 AWG)

Green-yellow

DR2.5/8.P.ADO

IEC

UL

1-2.5 mm²
1-2.5 mm²

16-14 AWG

1SNA299633R0600

Main technical data
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated cross section
2.5 mm²
Rated short-time withstand current (1s) 300 A
Protection
IP20

CSA

Rail

TH 15-5.5

Wire stripping
lengthTool

Screw clamp

33 1.29"100

Weight(1 pce) g
8.00

Mounting instructions

DR2.5/8.P.ADO

32 1.26"
31 1.22"Pkg

14 AWG
TorqueNEMA 180.315"

15.5 0.61"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R6

8 mm 0.315 in spacing

Accessories
Description

3

2

4

1
2
3
4

6.5 mm0.256 in
2.5 mm
0.098 inSemi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Tools

Grey
Grey

Type
BADRL
FEAD2
OUPAD
OUMAD
RCAL85

Part Number
1SNA199420R2100
1SNA199423R1000
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

50
20
1
1
1

2.00
1.30
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163069S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 147

DB1.5/6.ADO IDC terminal blocks
Miniblocks ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Easy base mounting thanks to the usage of flanges,–– Up to 2 wires per connection.

1SNC163142F0014

Ordering details
Description

Color

Type

Part Number

Feed-throughDB1.5/6.ADO

Grey

1SNA299513R2600

Main technical data

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG

Rail
Wire stripping
lengthTool

Screw clamp

28 1.10"100

Weight(1 pce) g
4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO
DB1.5/6.ADO

31 1.22"Pkg
pce

17.5 A / 1.5 mm² 20 A / 16 AWG
180 A
1000 V
600 V
8000 V
IP20
NEMA 1Torque

6

C

RoHS

US

cCSAusGost R

Notes
6 mm 0.236 in spacing

A: 2 holes DIA 3.2 mm for 3 mm screw max. with cylindrical head (not supplied)/L = (N blocks x 6) + (N blocks x 8)
Plate thickness 0.6 to 1.2 mm
BIntermediate mounting of DH blocks every 2 blocks (spacing 8 mm) or 3 blocks(spacing 6 mm)

A

Accessories
Description
1

3

2

4

1
2
3
4
5

5

End section kits
Jumper bars

2 poles17.5 A
3 poles
10 polesCircuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Grey
Orange

Grey

White

Type
FEAD4
BJADO6-2
BJADO6-3
BJADO6-10
FEAD6
OUPAD
OUMAD
RC65

Part Number
1SNA199439R2000
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
20
10
20
1
1
1

3.00
1.00
1.00
6.00
1.80
205.0029.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163070S0201 Rev. A

6

0.238"

The connecting capacity data for one Rigid: Solid/Stranded Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDB2.5/8.ADO IDC terminal blocks
Miniblocks ADO-ADO - 8 mm 0.315 in spacing
2.5 mm²
14 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Easy base mounting thanks to the usage of flanges,–– Up to 2 wires per connection.

1SNC163095F0014

Ordering details
Description

Color

Type

Part Number

pceWith 2 notches for wire
size 1-2.5 mm2(16-14 AWG)

Feed-throughGrey

DB2.5/8.ADO

1SNA299517R2200

Main technical data
DB2.5/8.ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

1-2.5 mm²
1-2.5 mm²

16-14 AWG

28 1.10"80.315"Rail
Wire stripping
lengthTool

Screw clamp

24 A / 2.5 mm² 25 A / 14 AWG
300 A
800 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CRoHS

8 mm 0.315 in spacing

100

Weight(1 pce) g
6.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

31 1.22"Pkg

US

cCSAusGost R

6

Notes
A: 2 holes DIA 3.2 mm for 3 mm screw max. with cylindrical head (not supplied)/L = (N blocks x 6) + (N blocks x 8)
Plate thickness 0.6 to 1.2 mm
BIntermediate mounting of DH blocks every 2 blocks (spacing 8 mm) or 3 blocks(spacing 6 mm)

A

Accessories

3

Description

2

4

1
2
3
4

End section kits
Circuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Grey
Grey

Type
FEAD4
FEAD6
OUPAD
OUMAD
RCAL85

Part Number
1SNA199439R2000
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA237000R0500

Pkg

Weightpce(1 pce) g

20
20
1
1
1

3.00
1.80
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163071S0201 - Rev. A

1

Technical data valid for copper conductors only.

PAGE 149

DH1.5/6.ADO IDC terminal blocks
Miniblocks ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²
16 AWG

Description–– The mini blocks are particularly designed for applications where space is very restricted,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Easy base mounting thanks to snap in mounting foot,–– Up to 2 wires per connection.

1SNC163093F0014

Ordering details
Description

Color

Type

Part Number

Feed-throughDH1.5/6.ADO

Grey

1SNA299529R0600

Main technical data

DH1.5/6.ADO

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.28-1.5 mm²
0.34-1.5 mm²

22-16 AWG

Rail
Wire stripping
lengthTool

Screw clamp

28 1.10"100

Weight(1 pce) g
4.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule

ADO

31 1.22"Pkg
pce

17.5 A / 1.5 mm² 20 A / 16 AWG
180 A
1000 V
600 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
0.238"

6

C

RoHS

US

cCSAusGost R

Notes

6
6 mm 0.236 in spacing//

L = (N blocks x 6) + (N blocks x 8)
N blocks = 3 blocks max. with 6 mm spacing
2 blocks max. with 8 mm spacing
Plate thickness 0.6 to 1.2 mm

3/4

6/8

3/4

3/4

Accessories
Description
1

3

2

4

1
2
3
4
5

Grey
Orange

Grey

White

Type
FEAD2
BJADO6-2
BJADO6-3
BJADO6-10
FEAD6
OUPAD
OUMAD
RC65

Part Number
1SNA199423R1000
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA199435R1400
1SNA178944R0400
1SNA179466R0600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
20
10
20
1
1
1

1.30
1.00
1.00
6.00
1.80
205.0029.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163072S0201 - Rev. A

5

2.5 mm
0.098 in
2 poles17.5 A
3 poles
10 polesCircuit separators 5 mm
0.197 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS6

PAGE 151

1SNC160100S0201

7

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Test & measurement
Technologies presentation			

154

Overview				

156

Screw clamp technology		Test disconnect with screwdriver sliding link		
6 mm² / 8 AWG

M6/8.ST		
With test

M6/8.ST1

157
158

M6/8.ST1.IP20

With insulated test sockets

159

M6/8.ST3

With insulated rod

160

M6/8.ST7

Feed-through161

M6/8.STA		

With test

162

Test disconnect with blade		
6 mm² / 8 AWG

D6/10.SNBTB1		
D6/10.SNBTB2		

With test

163
164

Test disconnect with plug		
4 mm² / 12 AWG

M4/6.ST			

165

10 mm² / 8 AWG

M10/10.ST-Sn

		

166

Test disconnect with push-turn knob		
6 mm² / 8 AWG

M6/8.STP1

With test

167

M6/8.STP		

With test

168

Spring loaded screw clamp technology		Test disconnect with screwdriver sliding link		
D6/8.ST1.RS

With test

169

D6/8.ST1.RS.IP20		

With insulated test sockets

170

7

1SNC160100S0201

6 mm² / 12 AWG

PAGE 153

Dedicated applications terminal blocks
Test & measurement - Screw clamp technology

Secure your measurement
operations
Our test & measurement terminal blocks
benefit from our long experience in theenergy applications.
A large choice of accessories make thetest & measurement operation easy andsecure.

RoHS

ISO 9001

A large choice of combinations and accessories

3 Test your circuits with flexibility using AJS9 test
sockets
The insulated test sockets AJS9 are available in 6 colors forconvenient circuit identification.
They are compatible with standard DIA. 4 mm test plugs(IEC 60010-031).
Fully operated by screwdriver (DIA. 3.5 mm).
4 Convenient circuit distribution with lateral jumpers
TE Connectivity provides a whole set of lateral jumpers
adapted to the various circuit configurations of our customers.
Secure your disconnect operation during short-circuiting
5 In non short-circuited position:–– The short circuiting bridge is opened. For security purpose,
the access to the disconnect sliding unit is blocked(in closed position).
6 In short-circuited position:–– The short circuiting bridge is first positioned, authorizing
access to the disconnect sliding unit for opening thecircuit.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

6

1

3

2

5

4

1SNC161164S0201

7

1 Short-circuit CT circuits safely and conveniently
TE connectivity's insulated short-circuit bridge allows secured
short-circuit position thanks to AJS9 test sockets tightening.
2 Adapted hook shape maintains the bridge on terminal
block in the non connected position.

Dedicated applications terminal blocks
Test & measurement - Typical schematic for measuring devices

Common point on the transformers
CT's
P1

L1
P1

L2
P1
S1

P2 S1

P2 S1

P2
S2

S2

S2

P

P

P

S

S

S

1

2

3

N

N

Voltage inputs
Measuring devices(ie: meters, protection relays…)

Current inputs

7

1SNC161165S0201

L3

PT's

PAGE 155

Dedicated applications terminal blocks
Test & measurement

Screw clamp technology

Test disconnect
with screwdriver sliding link

Test disconnect withinsulated rod sliding link

Feed-throughTest disconnect
with screwdriver sliding link

SectionIEC

UL/CSA

6 mm²

8 AWG

M6/8.ST

M6/8.ST1.IP20

M6/8.ST3

M6/8.ST7

M6/8.STA

6 mm 0.236 in

6 mm 0.236 in

8 mm 0.315 in

8 mm 0.315 in

6 mm 0.236 in

Test disconnect
with blade
SectionTest disconnect
with push-turn knob
1/4

IEC

UL/CSA4 mm²12 AWG

1/4

M4/6.ST
6 mm 0.236 in

6 mm²
10 mm²8 AWG

D6/10.SNBTB

M6/8.STP1

M6/8.STP

10 mm 0.394 in

8 mm 0.315 in

8 mm 0.315 in

8 AWG

M10/10.ST-Sn
10 mm 0.394 in

Spring loaded screw clamp technology

Test disconnect
with screwdriver sliding link
SectionIEC

UL/CSA

6 mm²

12 AWG

D6/8.ST1.RS.IP20
8 mm 0.315 in

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

1SNC161163S0201

7

Test disconnect
with plugM6/8.ST screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²

Secure your disconnect operations with the disconnect sliding link operated with a screwdriver.

8 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161214F0014

Disconnect

M6/8.STGrey

1SNA115236R1700

Main technical data

Mounting instructions
UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

18 - 8 AWG

18-8 AWG

Wire stripping
length13 mm
0.51 inScrew clamp
Tool

40 A / 6 mm²
720 A
630 V

30 A / 8 AWG

30 A / 8 AWG

150 V

150 V

IP20

NEMA 1

Flat screwdriverØ 5 mmØ 0.197 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.inIEC
1 conductor
per clamp

M6/8.ST

Torque56 2.21"48.5 1.91"

53.5 2.11"

77 3.03"25

Weight(1 pce) g
30.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

36 1.42"

RoHS

USR

CSA

Gost R

41 1.61"8 mm 0.315 in spacing

Accessories
Description
1

3

4

2
3
4

10 mm
5.2 mmEnd sections
1 mm
Jumper bars
20 poles
Lateral jumper bars 50 A

5

6

5
6

Circuit separators 3 mm
0.118 in
Test sockets
DIA 4 mm 0.157 in IP20

End stops

0.394 in
0.205 in
0.039 in
41 A

Dark grey
Grey
Black

Grey
Yellow
Black
Green

8

Grey
Blue
Red

9

10

Part Number

Pkg
pce

2

7

Type

DIA 4 mm 0.157 in
7 Test plugs
DIA 4 mm 0.157 in IP20
8 Short circuit
2 polesbridges
3 poles
4 poles
9 Fastening kits
Sub assembly post + screw + washer
10 Terminal block markers Blank card

Red
Yellow

White

BAM4
BAZ1
FEMT2
BJS8-20
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4SCFT2AJS9
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
AL4-M3
FC4-1
SC-JB8-2
SC-JB8-3
SC-JB8-4
EV8S
RC810

1SNK900001R0000
1SNK900002R0000
1SNA113629R2700
1SNA174789R0500
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA114522R0500
1SNA179726R0200
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206721R0100
1SNA167927R1000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA168401R0300
1SNA234000R0200

50
50
10
5
10
10
10
10
10
20
25
25
25
25
25
25
50
10
25
25
25
20
1

Weight(1 pce) g
14.00
5.30
2.00
3.20
14.00
6.60
7.84
9.00
4.50

7

5.00
3.60
3.60
3.60
3.60
3.60
1.10
11.00
2.00
3.40
4.70
3.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
pce

Feed-throughProfile aligned with M6/8.ST...

Grey

M6/8.ST7

1SNA115243R2600

25

Weight(1 pce) g
20.00

Technical data valid for copper conductors only.

PAGE 157

1SNC161055S0201

1

Color

M6/8.ST screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Secure your disconnect operations with the disconnect sliding link operated with a screwdriver,–– Ease your test operations with the 2 independent built-in test sockets compatible with DIA 4 mm 0.157 in test
plugs.

8 AWG

Ordering details
1SNC161213F0014

Description

Color

Type

Disconnect

With 2 test sockets
DIA 4 mm 0.157 in

M6/8.ST1Grey

1SNA115237R1000

Main technical data

1 conductor
per clamp

56 2.21"53.5 2.11"

48.5 1.91"

25

Weight(1 pce) g
30.00

Mounting instructions

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

18 - 8 AWG

18-8 AWG

Wire stripping
length13 mm
0.51 inScrew clamp
Tool

Flat screwdriverØ 5 mmØ 0.197 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

77 3.03"36 1.42"

Pkg
pce

IEC
M6/8.ST

Part Number

TorqueRated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

40 A / 6 mm²

30 A / 8 AWG

30 A / 8 AWG

720 A
630 V

150 V

150 V

NEMA

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

41 1.61"CE

8 mm 0.315 in spacing

RoHS

USR

CSA

Gost R

7

Accessories
Description
2

3

4

5

6

7

Type

Part Number

Pkg
pce

1
2
3

10 mm
9 mm
End sections
1 mm
Lateral jumper bars 50 A

4
5
6
7

Circuit separators 3 mm
0.118 in
Test plugs
DIA 4 mm 0.157 in IP20
Short circuit plugs DIA 4 mm 0.157 in
Terminal block markers Blank card

End stops

0.394 in
0.354 in
0.039 in

Dark grey
Grey
Black

Grey
Red
White

BAM4
BAZ1
FEMT2
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4SCFT2
FC4-1
BP8.A4
RC810

1SNK900001R0000
1SNK900002R0000
1SNA113629R2700
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA114522R0500
1SNA167927R1000
1SNA173888R2000
1SNA234000R0200

50
50
10
10
10
10
10
10
20
10
10
1

Weight(1 pce) g
14.00
4.70
2.00
14.00
6.60
7.84
9.00
4.50
11.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
pce

Feed-throughProfile aligned with M6/8.ST...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey

M6/8.ST7

1SNA115243R2600

25

Weight(1 pce) g
20.00

1SNC161109S0201

1

Color

M6/8.ST screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Terminal blocks especially designed for current transformers circuits:–– Easy and secured current measurement thanks to the two built-in test yellow sockets compatible with
IP20 DIA 4 mm 0.157 in test plugs,–– Convenient short-circuit operations with the PCS sliding short circuiting bridges from 2 to 4 poles,–– Tests sockets available as well in black, green, grey and blue.

8 AWG

1SNC161231F0014

Ordering details
Description

Color

Type

Part Number

Disconnect

With two yellow
test sockets
DIA 4 mm 0.157 in

M6/8.ST1.IP20

Grey

1SNA115971R1000

Main technical data
M6/8.ST

13.8
0.54"

1 conductor
per clamp

Mounting instructions
CSA

Rail

G32, TH 35-7.5,
TH 35-15

Rigid: Solid/Stranded
0.5 - 10 mm²
Flexible without ferrule
0.5 - 6 mm²
Flexible with insulated ferrule
Gauge
A5

18 - 8 AWG

18 - 8 AWG

Wire stripping
length13 mm
0.51 inScrew clamp
Tool

40 A / 6 mm²
720 A
630 V
8000 VIP20

30 A / 8 AWG

30 A / 8 AWG

150 V

150 V

Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.5 N.m
4.45 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.6 N.m
5.34 lb.in

Torque54 2.13"
49
56.5
1.93"
2.22"

25

Weight(1 pce) g
40.00

UL

IEC

77 3.03"

Pkg
pce

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

NEMA 1

Disconnect device
Tool
TorqueTest socketTool

36 1.42"
41 1.61"Torque8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

7

Gost R

Accessories
Description
2

3

4

5

6

Part Number

Pkg
pce

1
2
3

10 mm
9 mm
End sections
1 mm
Lateral jumper bars 50 A

4

Test sockets

End stops

0.394 in
0.354 in
0.039 in

Dark grey
Grey
Black

DIA 4 mm 0.157 in IP20

Black
Green
Grey
Blue
Red

7

Type

5
6

7

DIA 4 mm 0.157 in IP20
2 poles
3 poles
4 poles
Terminal block markers Blank card
Test plugs
Short circuitbridgesRed
Yellow

White

BAM4
BAZ1
FEMT2
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
FC4-1
SC-JB8-2
SC-JB8-3
SC-JB8-4
RC810

1SNK900001R0000
1SNK900002R0000
1SNA113629R2700
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA167927R1000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA234000R0200

50
50
10
10
10
10
10
10
25
25
25
25
25
10
25
25
25
1

Weight(1 pce) g
14.00
4.70
2.00
14.00
6.60
7.84
9.00
4.50
3.60
3.60
3.60
3.60
3.60
11.00
2.00
3.40
4.70
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
pce

Feed-throughProfile aligned with M6/8.ST...

Grey

M6/8.ST7

1SNA115243R2600

25

Weight(1 pce) g
20.00

Technical data valid for copper conductors only.

PAGE 159

1SNC161111S0201

1

Color

M6/8.ST screw clamp terminal blocks
Test disconnect with insulated rod sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Secure your disconnect operations with the disconnect sliding link operated with a screwdriver,–– Ease your test operations with the two independent built-in test sockets compatible with DIA 4 mm 0.157 in test plugs.

8 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161095F0014

Disconnect

With 2 test sockets
DIA 4 mm 0.157 in

M6/8.ST3Grey

1SNA115239R2200

Main technical data

Mounting instructions
UL

CSA

Rail

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

18 - 8 AWG

18-8 AWG

Wire stripping
length40 A / 6 mm²
720 A
630 V

30 A / 8 AWG

30 A / 8 AWG

150 V

150 V

IEC
1 conductor
per clamp

M6/8.ST

Screw clamp
Tool

53.5 2.11"

48.5 1.91"

56 2.21"

18.5
0.73"

Torque77 3.03"25

Weight(1 pce) g
30.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

NEMA

Disconnect device
Tool
TorqueG32, TH 35-7.5,
TH 35-15

Flat screwdriverØ 5 mmØ 0.197 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

36 1.42"

RoHS

USR

CSA

Gost R

41 1.61"8 mm 0.315 in spacing

7

Accessories
Description
2

3

4

5

6

7

Type

Part Number

Pkg
pce

1
2
3

10 mm
9 mm
End sections
1 mm
Lateral jumper bars 50 A

4
5
6
7

Circuit separators 3 mm
0.118 in
Test plugs
DIA 4 mm 0.157 in IP20
Short circuit plugs DIA 4 mm 0.157 in
Terminal block markers Blank card

End stops

Dark grey

0.039 in

Grey
Black

Grey
Red
White

BAM4
BAZ1
FEMT2
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4SCFT2
FC4-1
BP8.A4
RC810

1SNK900001R0000
1SNK900002R0000
1SNA113629R2700
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA114522R0500
1SNA167927R1000
1SNA173888R2000
1SNA234000R0200

50
50
10
10
10
10
10
10
20
10
10
1

Weight(1 pce) g
14.00
4.70
2.00
14.00
6.60
7.84
9.00
4.50
11.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
pce

Feed-throughProfile aligned with M6/8.ST...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey

M6/8.ST7

1SNA115243R2600

25

Weight(1 pce) g
20.00

1SNC161110S0201

1

Color

M6/8.ST screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

6 mm²

Profile aligned with M6/8 ST.

8 AWG

Ordering details
Description

Color

1SNC161150F0014

Feed-through56 2.21"53.5 2.11"

M6/8.ST7

1SNA115243R2600

Pkg

Weightpce(1 pce) g

25

20.00

Mounting instructions
UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

18 - 8 AWG

18-8 AWG

Wire stripping
length13 mm
0.51 inTool

Flat screwdriverØ 5 mmØ 0.197 in

40 A / 6 mm²
720 A
630 V

40 A / 8 AWG

40 A / 8 AWG

150 V

150 V

Torque0.8 - 1 N.m
7.1 - 8.9 lb.inIEC

M6/8.ST

48.5 1.91"

Grey

Part Number

Main technical data

1 conductor
per clamp

77 3.03"Type

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

36 1.42"
41 1.61"8 mm 0.315 in spacing

7

Accessories
Description
2

3

4

5

6

7

1
2
3
4

5
6
7

10 mm
9 mm
End sections
1 mm
Jumper bars
20 poles
Lateral jumper bars 2 poles
3 poles
4 poles
10 polesEnd stops

0.394 in
0.354 in
0.039 in
41 A
50 A

Circuit separators 3 mm
0.118 inFastening kits
Sub assembly post + screw + washer
Terminal block markers Blank card

Dark grey
Grey
Black

Grey
White

Type
BAM4
BAZ1
FEMT2
BJS8-20
PC8-2
PC8-3
PC8-4
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4
SCFT2
EV8S
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA113629R2700
1SNA174789R0500
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA114522R0500
1SNA168401R0300
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
10
5
10
10
10
10
10
10
10
10
20
20
1

14.00
4.70
2.00
3.20
3.00
4.00
6.00
14.00
6.60
7.84
9.00
4.50
3.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161069S0201

1

Color

Technical data valid for copper conductors only.

PAGE 161

M6/8.ST screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
6 mm²
8 AWG

Description–– Compact disconnect terminal blocks:–– Secure your disconnect operations with the disconnect orange sliding link operated with a screwdriver,–– Ease your test operations with the two built-in test sockets screws compatible with DIA 4 mm 0.157 in test
plugs.

Ordering details
1SNC161221F0014

Description

Color

Type

Disconnect

With 2 test sockets
DIA 4 mm 0.157 inGrey

M6/8.STA

1SNA115359R0200

Main technical data

1 conductor
per clamp

CSA

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

22 - 8 AWG

30 A / 6 mm²
480 A
500 V

50 A / 8 AWG
600 V

IP20

NEMA 1

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length11 mm
0.43 inScrew clamp
Tool

Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

64 2.52"

61.5 2.42"

Torque56.5 2.22"

25

Weight(1 pce) g
30.00

Mounting instructions
UL

61 2.40"

28 1.10"

Pkg
pce

IEC

M6/8.ST

Part Number

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

33 1.30"
CE

RoHS

USR

Gost R

8 mm 0.315 in spacing

7

Accessories
Description
1

3

5

4

6

Type

Part Number

Pkg
pce

1

End stops2

End sections

3
4

Jumper bars
1 poles
24 A
Lateral jumper bars 2 poles
50 A
3 poles
4 poles
10 polesTest plugs
DIA 4 mm 0.157 in IP20
Short circuit plugs
Terminal block markers Blank card

5
6
7

10 mm
9 mm
3 mm

0.394 in
0.354 in
0.118 in

Dark grey
Grey
Grey
Black

Red
White

BAM4
BAZ1
FEMT4
FEMSTA
AD2.5
PC8-2
PC8-3
PC8-4
PC8-10
FC4-1
BP8.A4
RC810

1SNK900001R0000
1SNK900002R0000
1SNA114778R0500
1SNA116979R2100
1SNA114205R2000
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA167927R1000
1SNA173888R2000
1SNA234000R0200

50
50
10
10
50
10
10
10
10
10
10
1

Weight(1 pce) g
14.00
4.70
5.60
3.60
1.60
3.00
4.00
6.00
14.00
11.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161031S0201

7

2

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD6/10.SNBTB screw clamp terminal blocks
Test disconnect with blade - 10 mm 0.394 in spacing
Description

6 mm²–– Ease your disconnect operations with the disconnect blade,–– Ease your test operations with built-in test sockets compatible with DIA 4 mm 0.157 in test plugs.

Ordering details

1SNC161163F0014

Description
Disconnect

Color
With 1 isolated
test socket
DIA 4 mm 0.157 in

Type
Grey

D6/10.SNBTB1

1SNA115928R1500

Main technical data
1 conductor
per clamp

UL

CSA

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

58.7 2.31"

51.2 2.01"

72 2.83"

64.5 2.53"

41 1.61"

Weight(1 pce) g

20

25.00

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

12 mm
0.47 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.8 N.m
7.1 lb.in

82 3.22"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg
pce

Mounting instructions
IEC

D6/10.SNBTBPart Number

15 A / 6 mm²
720 A
500 V
6000 V
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

10 mm 0.394 in spacing

7

Accessories
Description

3

2

4

1
2
3
4

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2 mm
0.079 in
Test plugs
DIA 4 mm 0.157 in IP20
Terminal block markers Blank card
End stops

Type

Dark grey
Grey
Red
White

BAM4
BAZ1
FED10S1
FC4-1
RC1010Part Number
1SNK900001R0000
1SNK900002R0000
1SNA215999R2100
1SNA167927R1000
1SNA238000R1600

Pkg

Weightpce(1 pce) g

50
50
20
10
1

14.00
5.30
3.35
11.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161154S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 163

D6/10.SNBTB screw clamp terminal blocks
Test disconnect with blade - 10 mm 0.394 in spacing
Description

6 mm²–– Ease your disconnect operations with the disconnect blade,–– Ease your test operations with built-in test sockets compatible with DIA 4 mm 0.157 in test plugs.

Ordering details

1SNC161162F0014

Description
Disconnect

Color
With 2 isolated
test sockets
DIA 4 mm 0.157 in

Type
Grey

D6/10.SNBTB2

1SNA115929R1600

Main technical data
1 conductor
per clamp

UL

CSA

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

58.7 2.31"

51.2 2.01"

72 2.83"

64.5 2.53"

41 1.61"

Weight(1 pce) g

20

25.00

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

12 mm
0.47 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.8 N.m
7.1 lb.in

82 3.22"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg
pce

Mounting instructions
IEC

D6/10.SNBTBPart Number

15 A / 6 mm²
720 A
500 V
6000 V
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

10 mm 0.394 in spacing

7

Accessories
Description
1

3

2

3

1
2
3
4

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2 mm
0.079 in
Test plugs
DIA 4 mm 0.157 in IP20
Terminal block markers Blank card
End stops

Color

Type

Dark grey
Grey
Red
White

BAM4
BAZ1
FED10S1
FC4-1
RC1010Part Number
1SNK900001R0000
1SNK900002R0000
1SNA215999R2100
1SNA167927R1000
1SNA238000R1600

Pkg

Weightpce(1 pce) g

50
50
20
10
1

14.00
5.30
3.35
11.00
1.30

1SNC161155S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.ST screw clamp terminal blocks
Test disconnect with plug - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description–– Test disconnect terminal blocks operated with plug,–– Dedicated "make before break" plug for current circuit (green plug) or "break before make" for voltage circuit(red plug).

Ordering details
Description

Color

Type

Pkg

Part Number

1SNC161211F0014

pce

Disconnect

55.5 2.19"
48 1.89"

53 2.09"

6 mm 0.236 in spacing

1SNA115313R1400
1SNA115314R1500

20
20

Mounting instructions
Rail

G32, TH 35-7.5,
TH 35-15

Rigid: Solid/Stranded
0.5 - 4 mm²
Flexible without ferrule
0.5 - 4 mm²
Flexible with insulated ferrule
Gauge
A4

22-12 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

5 A / 4 mm²
480 A
500 V

5 A / 12 AWG
Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IP10

UL

150 V
NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

29 1.14"

M4/6.ST.Sn
M4/6.ST.Au

CSA

IEC

M4/6.ST

24 0.94"

Grey

Main technical data
1 conductor
per clamp

53 2.09"

Tinned contact bladesGold contact blades

Weight(1 pce) g
14.00
14.00

RoHS

CSA

Gost R

Utilization of each type of plug
Number of operations: 200
On request, the plugs can be replaced by an
insertable printed circuit for diagnosis testing.

BNT1 ("voltage" plug)

BNT2 ("polarity" plug)

BNT3 ("current" plug)7

1st step: the plug cuts the circuit.
2nd step: the test circuit connection is made.

Plug not equipped with pins cuts the circuit.

1st step: the test circuit is established
2nd step: the plug opens the circuit.

Accessories

3

2

4

5

6

7

8

9

10

Color

Type

Part Number

Pkg
pce

1

10 mm
0.394 in
5.2 mm0.205 in2 End sections
2.5 mm
0.098 in3 Jumper bars
1 poles
24 A
4 Lateral jumper bars 10 poles
35 A
5 Shield connectors
6 Short circuit plugs "Polarity" plug
"Voltage" plug
"Current" plug
7 Assembly pins for plugs
8 Pins
0.5 mm²
24-20 AWG
1 mm²
18 AWG
1.5 mm²
16 AWG
2.5 mm²
14 AWG
4 mm²
12 AWG
9 Tools
Connecting capacity: 1 to 2.5 mm²
10 Terminal block markers Blank card
End stops

Dark grey
Grey
Grey

Grey
Red
Green

White

BAM4
BAZ1
FEMT3
AD2.5
PC61-10
CBM5
BNT2
BNT1
BNT3
CVABM
BRC-0.5
BRC-1
BRC-1.5
BRC-2.5
BRC-4
PSC
RC610

1SNK900001R0000
1SNK900002R0000
1SNA114328R2200
1SNA114205R2000
1SNA163311R2200
1SNA178745R1400
1SNA114329R2300
1SNA199135R1700
1SNA199136R1000
1SNA183436R0500
1SNA174558R0500
1SNA173906R2200
1SNA173907R2300
1SNA173908R0400
1SNA174601R0100
1SNA173181R1300
1SNA233000R0100

50
50
20
50
10
50
20
20
20
10
10
10
10
10
10
1
1

Weight(1 pce) g
14.00
5.30
2.70
1.60
5.00
3.00
8.00
8.00
0.40
1.40
2.00
2.00
2.00
2.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 165

1SNC161140S0201 - Rev. A

Description1M10/10.ST-Sn screw clamp terminal blocks
Test disconnect with plug - 10 mm 0.394 in spacing
10 mm²
8 AWG

Description–– Test disconnect terminal blocks operated with plug,–– Dedicated "make before break" plug for current circuit (green plug) or "break before make" for voltage circuit(red plug).

Ordering details
Description

Color

Type

Pkg

Part Number

1SNC161224F0014

pce

Disconnect

Tinned contact blades

Grey

M10/10.ST-Sn

1SNA115539R1700

Main technical data

Mounting instructions
IEC

1 conductor
per clamp

UL

Rigid: Solid/Stranded
0.5-16 mm²
Flexible without ferrule
0.5-10 mm²
Flexible with insulated ferrule
Gauge
B6

CSA

Rail

G32, TH 35-7.5,
TH 35-15

8 AWG

Wire stripping
length

12 mm
0.472 inTool

Flat screwdriverØ 5.5 - 6 mm
Ø 0.217 - 0.236 in

Torque1.2 - 1.4 Nm
10.6 - 12.3 lb.in

M10/10.ST-Sn

59 2.32"51.5 2.02"

55.5 2.22"

63 2.48"20

Weight(1 pce) g
27.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

15 A / 10 mm²1200 A
500 V
IP2010 A / 8 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

CSA

Gost R

Utilization of each type of plug
29 1.14"34 1.34"

Number of operations: 200
On request, the plugs can be replaced by an
insertable printed circuit for diagnosis testing.

BNT1 ("voltage" plug)

BNT2 ("polarity" plug)

BNT3 ("current" plug)

1st step: the plug cuts the circuit.
2nd step: the test circuit connection is made.

Plug not equipped with pins cuts the circuit.

1st step: the test circuit is established
2nd step: the plug opens the circuit.

10 mm 0.394 in spacing

7

Accessories
2

3

4

5

6

7

9

8

10

Color

Type

Part Number

Pkg
pce

1

10 mm
0.394 in
5.2 mm0.205 in2 End sections
2.5 mm
0.098 in3 Jumper bars
2 poles
57 A
3 poles
4 poles
5 poles
10 poles
4 Lateral jumper bars 10 poles
70 A
5 Shield connectors
6 Short circuit plugs "Polarity" plug
"Voltage" plug
"Current" plug
7 Assembly pins for plugs
8 Pins
0.5 mm²
24-20 AWG
1 mm²
18 AWG
1.5 mm²
16 AWG
2.5 mm²
14 AWG
4 mm²
12 AWG
9 Tools
Connecting capacity: 1 to 2.5 mm²
10 Terminal block markers Blank card
End stops

Dark grey
Grey

Grey
Red
Green

White

BAM4
BAZ1
FEMT5
BJMI10-2
BJMI10-3
BJMI10-4
BJMI10-5
BJMI10-10
PC10-10
CBM5
BNT2
BNT1
BNT3
CVABM1
BRC-0.5
BRC-1
BRC-1.5
BRC-2.5
BRC-4
PSC
RC1010

1SNK900001R0000
1SNK900002R0000
1SNA116781R1300
1SNA176675R0400
1SNA176676R0500
1SNA176677R0600
1SNA176678R1700
1SNA176679R1000
1SNA163315R2600
1SNA178745R1400
1SNA114329R2300
1SNA199135R1700
1SNA199136R1000
1SNA116783R1500
1SNA174558R0500
1SNA173906R2200
1SNA173907R2300
1SNA173908R0400
1SNA174601R0100
1SNA173181R1300
1SNA238000R1600

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

50
50
20
10
10
10
10
10
10
50
20
20
20
20
10
10
10
10
10
1
1

Weight(1 pce) g
14.00
5.30
3.00
5.00
8.00
11.00
13.00
27.00
23.00
3.00
8.00
8.00
1.40
2.00
2.00
2.00
2.00
1.30

1SNC161147S0201 - Rev. A

Description1

M6/8.STP screw clamp terminal blocks
Disconnect with push-turn knob - with test socket - 8 mm 0.315 in spacing
6 mm²

1/4

8 AWG

Description–– Ease your disconnect operations with the disconnect ¼ turn push-turn knob,–– Possibility to seal in the open and closed position,–– Ease your test operations with the built-in test socket.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161217F0014

qty

Disconnect

64 2.52"

61.5 2.42"

M6/8.STP1IECUL

1SNA115529R1500

25

Mounting instructions

Connecting capacity

M6/8.STP

56.5 2.22"

Grey, orange

Main technical data
1 conductor
per clamp

55.5 2.19"

With 2 test sockets
DIA 4 mm 0.157 in

Weight(1 pce) g
21.00

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

15 A / 6 mm²
720 A
500 V
IP10

CSA

Rail

G32, TH 35-7.5,
TH 35-15

8 AWG

Wire stripping
length11 mm
0.433 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.8 - 1 N.m
7.1 - 8.9 lb.in

15 A / 8 AWG
600 V
NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

CSA

Gost R

25.5 1.00"

Notes

30.5 1.20"

8 mm 0.315 in spacingA

1

A: Closing operation

B

1

B: Opening operation
1: Push2: Turn
3: Stop

2

7

2
3

3

Accessories
2

3

4

5

6

Color

Part Number

Pkg
qty

1

6

10 mm
0.394 in
9 mm
0.354 inEnd sections
2.8 mm0.110 in
Lateral jumper bars 2 poles
50 A
3 poles
4 poles
10 polesCircuit separators 1 mm
0.039 in
Test plugs
DIA 4 mm 0.157 in
DIA 4 mm 0.157 in IP20
Short circuit plugs DIA 4 mm 0.157 in

7

With test DIA 4 mm 0.157 in
Terminal block markers Blank card

2
3

4
5

End stops

Dark grey
Grey

Grey
White
Red
Red

7

Type

Beige
White

BAM4
BAZ1
FEMT1
PC8-2
PC8-3
PC8-4
PC8-10
SCFT1
FC4
FC4-1
BP8.A4
BNSTP2
BNSTP1RC810

1SNK900001R0000
1SNK900002R0000
1SNA113137R0200
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA103588R2600
1SNA167860R0100
1SNA167927R1000
1SNA173888R2000
1SNA196789R2400
1SNA196792R1700
1SNA234000R0200

50
50
50
10
10
10
10
20
10
10
10
20
20
1

Weight(1 pce) g
14.00
4.70
2.00
3.00
4.00
6.00
14.00
20.00
10.00
11.00
10.00
14.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
qty

Feed-throughProfile aligned with M6/8 STP...

Grey

M6/8.STP3

1SNA115500R2500

25

Weight(1 pce) g
21.00

Technical data valid for copper conductors only.

PAGE 167

1SNC161108S0201 - Rev. B

Description1

M6/8.STP screw clamp terminal blocks
Disconnect with push-turn knob - with test socket - 8 mm 0.315 in spacing
6 mm²

1/4

8 AWG

Description–– Ease your disconnect operations with the disconnect ¼ turn push-turn knob,–– Possibility to seal in the open position,–– Ease your test operations with the built-in test socket.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161210F0014

qty

Disconnect

With 2 test sockets
DIA 4 mm 0.157 inGrey, yellow
Grey, black
Grey, redM6/8.STP
M6/8.STP
M6/8.STP

IEC

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-8 AWG

8 AWG

Wire stripping
length11 mm
0.433 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.8 - 1 N.m
7.1 - 8.9 lb.in

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge

60 2.37"52.5 2.07"

57.5 2.27"

55.5 2.19"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

15 A / 6 mm²
180 A
500 V

40 A / 8 AWG

15 A / 8 AWG

600 V

600 V

IP10

NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

25.5 1.00"
30.5 1.20"

25
25
25

Mounting instructions

Connecting capacity

M6/8.STP

1SNA115277R2000
1SNA105141R2700
1SNA105142R2000

Weight(1 pce) g
21.00
21.00
21.00

USR

CSA

Gost RNotes

8 mm 0.315 in spacingA

1

A: Closing operation

B

1

B: Opening operation
1: Push2: Turn7

3: Stop2

2
3

3

Accessories
Description

2

Color

Part Number

Pkg
qty

1

6

10 mm
0.394 in
9 mm
0.354 inEnd sections
2.8 mm0.110 in
Lateral jumper bars 2 poles
50 A
3 poles
4 poles
10 polesCircuit separators 1 mm
0.039 in
Test plugs
DIA 4 mm 0.157 in
DIA 4 mm 0.157 in IP20
Short circuit plugs DIA 4 mm 0.157 in

7

With test DIA 4 mm 0.157 in
Terminal block markers Blank card

3

4

2
3

5

6

4
5

End stops

Dark grey
Grey

Grey
White
Red
Red

7

Type

Beige
White

BAM4
BAZ1
FEMT1
PC8-2
PC8-3
PC8-4
PC8-10
SCFT1
FC4
FC4-1
BP8.A4
BNSTP2
BNSTP1RC810

1SNK900001R0000
1SNK900002R0000
1SNA113137R0200
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA103588R2600
1SNA167860R0100
1SNA167927R1000
1SNA173888R2000
1SNA196789R2400
1SNA196792R1700
1SNA234000R0200

50
50
50
10
10
10
10
20
10
10
10
20
20
1

Weight(1 pce) g
14.00
4.70
2.00
3.00
4.00
6.00
14.00
20.00
10.00
11.00
10.00
14.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
qty

Feed-throughProfile aligned with M6/8 STP...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey

M6/8.STP3

1SNA115500R2500

25

Weight(1 pce) g
21.00

1SNC161067S0201 - Rev. B1

D6/8.ST.RS spring loaded screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Mainly dedicated to energy markets for security purposes on CT circuits,–– Security: specific shape in linking bar to lock the ferrule, spring clamp can maintain contact pressure even ifscrew clamp is loose.

Ordering details
1SNC161277F0014

Description

D6/8.ST.RS

78.4 3.08"

55.8 2.19"

85.6 3.37"

Color

Disconnect

Type
Grey

Part Number

D6/8.ST.RS

1SNA115914R0700

Main technical data

Weight(1 pce) g

32

28.00

Mounting instructions
IEC

1 conductor
per clamp

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule

Lugs

Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg
pce

BS
TS 5018

CSA

Rail
Wire stripping
length

0.28-2.5 mm²

Tool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.8 - 1 Nm
7.1 - 8.9 lb.in

A5
24 A / 6 mm²
720 A
400 V
6000 V

G32, TH 35-7.5,
TH 35-15
16 mm
0.51 in

NEMA

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

45 1.77"

Each screw clamp holds up to 2 bent lugs as shown(not supplied)

8 mm 0.315 in spacing

7

Description
1

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5

Fastening kits
Test sockets

4

6

Color
End stops 0.394 in
0.205 in
1 mm
0.039 in
2 poles
41 A
3 poles
4 poles
20 polesSub assembly post + screw + washer
DIA 4 mm 0.157 in IP20

Type

Dark grey
Grey

Yellow
Black
Green
Grey
Blue

7

Red

8
6
7
8

DIA 4 mm 0.157 in
Test plugs
DIA 4 mm 0.157 in IP20
Short circuit
2 polesbridges
3 poles
4 poles
Terminal block markers Blank card

Red
Yellow

White

BAM4
BAZ1
FEM8T6
BJS8
BJS8-20
EV6I
AJS9
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
AL4-M3
FC4-1
SC-JB8-2
SC-JB8-3
SC-JB8-4
RC810Part Number
1SNK900001R0000
1SNK900002R0000
1SNA215266R0100
1SNA164581R1300
1SNA164582R1400
1SNA164583R1500
1SNA174789R0500
1SNA206394R0200
1SNA179726R0200
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206721R0100
1SNA167927R1000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA234000R0200

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
5
20
25
25
25
25
25
25
50
10
25
25
25
1

14.00
5.30
4.40
3.10
3.10
3.10
3.20
2.00
3.60
3.60
3.60
3.60
3.60
3.60
1.10
11.00
2.00
3.40
4.70
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 169

1SNC161153S0201 - Rev. A

Accessories

D6/8.ST.RS spring loaded screw clamp terminal blocks
Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing
Description

6 mm²–– Mainly dedicated to energy markets for security purposes on CT circuits,–– Security: specific shape in linking bar to lock the ferrule, spring clamp can maintain contact pressure evenif screw clamp is loose.

Ordering details

1SNC161233F0014

Description

D6/8.ST.RS

Disconnect

Color
With 2 yellow test sockets
DIA 4 mm 0.157 in

Type
Grey

Part Number

D6/8.ST1.RS.IP20

1SNA115831R0400

BS
TS 5018

Rail

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule

Lugs

Flexible with insulated ferrule
Gauge

CSA

Wire stripping
length

0.28-2.5 mm²Screw clamp
Tool

A5
Torque78.4 3.08"

24 A / 6 mm²
720 A
400 V
6000 V

Disconnect device
Tool
NEMA

Torque55.8 2.19"

15.1
0.59"

85.6 3.37"

Weight(1 pce) g

32

38.00

Mounting instructions
IEC

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg
pce

Test socket
Tool
Torque45 1.77"

G32, TH 35-7.5,
TH 35-15
16 mm
0.51 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
0.8 - 1 Nm
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.inØ 3.5 mm
Ø 0.138 in
0.6 N.m
5.34 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

CE

RoHS

Gost R

7

Each screw clamp holds up to 2 bent lugs as shown(not supplied)

Description
1

3

2

1

End stops

4

2
3
4

End sections
Jumper bars
Test sockets

Color
10 mm
0.394 in
5.2 mm0.205 in
1 mm
0.039 in
1 poles
24 A
DIA 4 mm 0.157 in IP20

Dark grey
Grey
Grey
Black
Green
Grey
Blue

5

7

6

Red

5
6

7

DIA 4 mm 0.157 in IP20
2 poles
3 poles
4 poles
Terminal block markers Blank card
Test plugs
Short circuitbridgesRed
Yellow

White

Type
BAM4
BAZ1
FEM8T6
AD2.5
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
FC4-1
SC-JB8-2
SC-JB8-3
SC-JB8-4
RC810Part Number
1SNK900001R0000
1SNK900002R0000
1SNA215266R0100
1SNA114205R2000
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA167927R1000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA234000R0200

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
10
50
25
25
25
25
25
10
25
25
25
1

14.00
5.30
4.40
1.60
3.60
3.60
3.60
3.60
3.60
11.00
2.00
3.40
4.70
8.20

1SNC161095S0201 - Rev. A

Accessories

7

PAGE 171

1SNC164011S0201

8

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Pluggable
Technologies presentation		
Overview			

174
175

Screw clamp technology		Feed-through		
2.5 mm² / 12 AWG
MA2.5/5-CPE		
MA2.5/5-2CPE

176
178

Double deck		
2.5 mm² / 12 AWG
MA2.5/5D2-2CPE
MA2.5/5.D-2CPE

180
181

2 feed-through circuits
1 feed-through circuit

Disconnect with blade		
2.5 mm² / 12 AWG
MA2.5/5-SNB-CPE		182

ADO technology
Feed-through		
1.5 mm² / 16 AWG
D1.5/7.ADO-CPE
D1.5/7.2ADO-CPE
2.5 mm² / 14 AWG
D2.5/7.ADO-CPE
D2.5/7.2ADO-CPE

183
185
184
186

8

1SNC164011S0201

1 ADO - 1 pluggable
2 ADO - 1 pluggable
1 ADO - 1 pluggable
2 ADO - 1 pluggable

PAGE 173

Dedicated applications terminal blocks
Pluggable

Optimize your equipment
assembly process!
TE connectivity’s pluggable terminal blocks offer the possibility to use pre-assembled cables and connectors which
improve wiring efficiency.
Pluggable technology offers following advantages:–– Wiring can be pre-defined and pre-tested before final
assembling–– During assembling, the pre-assembled cables help insaving time (plug & play solution) and reduce wiring errors–– During servicing, rail assemblies or components can bequickly replaced.
The preferred solution for OEM’s and panel builders
handling cabinets made of multiple separate modules.

RoHS

ISO 9001

A large choice of solutions and technologies

PI-Spring screwless pluggable technology
Our PI-Spring pluggable range combines fast assembly andfast wiring thanks to our exclusive tool-free direct insertion
connection technology.
The range features functions adapted to OEM’s applications
such as 2 jumper channels for distribution, testing,high density
wiring with dual connection on both side.
Find more in out SNK series catalog.
ADO System® screwless pluggable technology
Combines fast assembly with the Fastest and the Most Reliable Connection on the Market.
Our ADO System ® range features high ratings 4 mm²/24 A
max and high density wiring with dual connection and up to
2 wires per ADO System ® connection.

Screw clamp pluggable terminal
block

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSADO System® pluggable terminalblock

1SNC164010S0201

8

Screw clamp pluggable technology
TE connectivity’s screw clamp pluggable range combines theadvantage of a fast connection associated with the standard
easy to use screw technology.
The range features various functions such as: feed-through,neutral, double deck, disconnect and fuse.

Dedicated applications terminal blocks
Pluggable

Screw clamp technology

Feed-throughDouble deck

SectionIEC

UL/CSA

2.5 mm²

12 AWG

MA2.5/5-CPE

MA2.5/5-2CPE

MA2.5/5D2-2CPE

MA2.5/5.D-2CPE

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

Disconnect with blade
SectionIEC

UL/CSA

2.5 mm²

12 AWG

MA2.5/5-SNB-CPE
5 mm 0.197 in

8

ADO technology

Feed-through

UL/CSA

1.5 mm²

16 AWG

2.5 mm²

14 AWG

D1.5/7.ADO-CPE

1SNC160060S0201

SectionIEC

D1.5/7.2ADO-CPE

7.62 mm 0.300 in

7.62 mm 0.300 in

D2.5/7.ADO-CPE

D2.5/7.2ADO-CPE

7.62 mm 0.300 in

7.62 mm 0.300 in

PAGE 175

MA2.5/5-CPE pluggable terminal blocks
Feed-through - 5.08 mm 0.200 in spacing
2.5 mm²
12 AWG

Description–– Save in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– They are particularly well adapted to solve the connecting problems of equipment composed of sub-assemblies (complex machines such as elevators or trains, panel boards with extension boxes...),–– They can then be easily connected through patchcords with CPFT2 plugs connected to the pluggable terminal blocks outputs.

1SNC161306F0014

Ordering details
Description
Feed-throughColor
1 feed-through circuit

Type
Grey
Blue

Part Number

MA2.5/5-CPE
MA2.5/5-CPE

1SNA400814R0000
1SNA400827R0000

Main technical data
1 conductor
per clamp
44.5 1.75"

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

UL

CSA

55.5 2.18"
48 1.89"

53 2.09"

1.4 0.06"

50
50

7.00
7.00

24-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

1.4 0.06"

18 0.71"

Weight(1 pce) g

Mounting instructions
IEC

MA2.5/5-CPE

Pkg
pce

12 A / 2.5 mm² 10 A / 12 AWG
300 A
320 V
300 V
4000 V
IP20
NEMA 1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

23 0.91"

C

CE

RoHS

USR CNRUS

cCSAusGost R

5.08 mm 0.200 in spacing

Accessories

1

3

2

4

1
2
3
4

5
5

6

6
7
8

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inEnd section-flange kit (R+L)
Jumper bars
2 poles
24 A
3 poles
4 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inShield connectors
Coding pegs
End stops

7

8

9

9

10

10 Female plugs
5.08 mmwires perpendicular

11

Female plugs
wires parallel

5.08 mm0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 poles

11 Terminal block markers Blank card

Dark grey
Grey
Grey

Grey

Black

Black

White

Type
BAM4
BAZ1
FEM6
ENS.FE-BCP
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-10
PC5-2
PC5-10
EL6
CBM5
COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510Part Number
1SNK900001R0000
1SNK900002R0000
1SNA400824R0000
1SNA400819R0000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA173627R2100
1SNA178745R1400
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
50
10
10
120
80
60
20
120
80
60
20
1

14.00
5.30
2.40
7.00
3.30
5.00
6.70
16.90
1.80
6.00
0.10
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

1SNC164001S0201 - Rev. B

Description

8

MA2.5/5-CPE pluggable terminal blocks
Feed-through - 5.08 mm 0.200 in spacing
2.5 mm²
12 AWG

Description–– Save in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– They are particularly well adapted to solve the connecting problems of equipment composed of sub-assemblies (complex machines such as elevators or trains, panel boards with extension boxes...),– – They can then be easily connected through patchcords with CPFT2 plugs connected to the pluggableterminal blocks outputs.

1SNC161309F0014

Ordering details
Description
Feed-throughColor
1 feed-through circuitwith partition

Type
Grey

Part Number

MA2.5/5-CPE.1

1SNA400822R0000

Main technical data
UL

CSA

55.5 2.18"
48 1.89"

53 2.09"

1.4 0.06"

1.4 0.06"

18 0.71"

50

7.00

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

MA2.5/5-CPE

44.5 1.75"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

24-12 AWG

12 A / 2.5 mm² 10 A / 12 AWG
300 A
320 V
300 V
4000 V
IP20
NEMA 1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

23 0.91"

C

CE

RoHS

USR CNRUS

cCSAusGost R

5.08 mm 0.200 in spacing

Accessories
1

1

3

4

2
3
4

5

6

5
6
7
8

8

9

10

11

Type

Part Number

BAM4
BAZ1
FEM6
ENS.FE-BCP
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-10
PC5-2
PC5-10
EL6
CBM5
COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510

1SNK900001R0000
1SNK900002R0000
1SNA400824R0000
1SNA400819R0000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA173627R2100
1SNA178745R1400
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Pkg
pce

2

7

Color

9

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inEnd section-flange kit (R+L)
Jumper bars
2 poles
24 A
3 poles
4 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inShield connectors
Coding pegs
End stops

Female plugs
wires parallel

5.08 mm

10 Female plugs
5.08 mmwires perpendicular

0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 poles

11 Terminal block markers Blank card

Dark grey
Grey

Grey

Black

Black

White

50
50
20
10
10
10
10
10
10
10
10
50
10
10
120
80
60
20
120
80
60
20
1

8

Weight(1 pce) g
14.00
5.30
2.40
7.00
3.30
5.00
6.70
16.90
1.80
6.00
0.10
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Technical data valid for copper conductors only.

PAGE 177

1SNC164002S0201 - Rev. B

Description

MA2.5/5-2CPE pluggable terminal blocks
Feed-through - 5.08 mm 0.200 in spacing
2.5 mm²

1SNC161304F0014

12 AWG

Description–– Save in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– They are particularly well adapted to solve the connecting problems of equipment composed of sub-assemblies (complex machines such as elevators or trains, panel boards with extension boxes...),–– They can then be easily connected through patchcords with CPFT2 plugs connected to the pluggable terminal blocks outputs.

Ordering details
Description
Feed-throughColor
1 feed-through circuit

Type
Grey
Blue

Part Number

MA2.5/5-2CPE
MA2.5/5-2CPE

1SNA400817R0000
1SNA125711R1500

Main technical data
MA2.5/5-2CPE

52.5 2.07"
45 1.77"

50 1.97"

58.5 2.30"

26 1.02"
31 1.22"Weight(1 pce) g

50
50

7.00
7.00

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

24-12 AWG

12 A / 2.5 mm² 10 A / 12 AWG
300 A
320 V
300 V
4000 V
IP20
NEMA 1

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length10 mm
0.394 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

Gost R

5.08 mm 0.200 in spacing

Description
1

2

1
2
3

3

4

5

6

4
5
6

7

9

8

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inJumper bars
2 poles
24 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
Coding pegs
End stops

7

Female plugs
wires parallel

5.08 mm8

Female plugs
5.08 mmwires perpendicular9

Terminal block markers Blank card

0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 polesDark grey
Grey

Grey

Black

Black

White

Type
BAM4
BAZ1
FE2CPE
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
PC5-2
PC5-10
EL6COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510Part Number
1SNK900001R0000
1SNK900002R0000
1SNA400826R0000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA173627R2100
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
120
80
60
20
120
80
60
20
1

14.00
5.30
2.50
3.30
5.00
6.70
8.40
16.90
1.80
6.00
0.10
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

1SNC164003S0201 - Rev. A

Accessories

8MA2.5/5-2CPE pluggable terminal blocks
Feed-through - 5.08 mm 0.200 in spacing
Description

2.5 mm²–– Save in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– They are particularly well adapted to solve the connecting problems of equipment composed of sub-assemblies (complex machines such as elevators or trains, panel boards with extension boxes...),– – They can then be easily connected through patchcords with CPFT2 plugs connected to the pluggableterminal blocks outputs.
1SNC161311F0014

12 AWG

Ordering details
Description
Feed-throughColor
1 feed-through circuit
for use in combination
with disconnect blocks

Type
Grey

Part Number

MA2.5/5-2CPE1-Pb

Main technical dataIEC52.5 2.07"
45 1.77"

50 1.97"

58.5 2.30"

26 1.02"
31 1.22"Weight(1 pce) g

50

7.00

Mounting instructions

MA2.5/5-2CPE

1 conductor
per clamp

1SNA400821R0000

Pkg
pce

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

24-12 AWG

12 A / 2.5 mm² 10 A / 12 AWG
300 A
320 V
300 V
4000 V
IP20
NEMA 1

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length10 mm
0.394 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

5.08 mm 0.200 in spacingRoHS

USR CNR

Gost R

Accessories

8

Description
2

4

5

6

Part Number

BAM4
BAZ1
FE2CPE
PC5-2
PC5-10
COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510

1SNK900001R0000
1SNK900002R0000
1SNA400826R0000
1SNA113542R1000
1SNA113544R1200
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Pkg
pce

1
2
3

3

Type

4

10 mm
5.2 mmEnd sections
2.8 mmLateral jumper bars 2 poles
10 polesCoding pegs

End stops

5

Female plugs
wires parallel

5.08 mm6

Female plugs
5.08 mmwires perpendicular7

Terminal block markers Blank card

70.394 in
0.205 in
0.110 in
30 A

0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 polesDark grey
Grey
Grey

Black

Black

White

50
50
20
10
10
10
10
120
80
60
20
120
80
60
20
1

Weight(1 pce) g
14.00
5.30
2.50
1.80
6.00
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC164004S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 179

MA2.5/5D-2CPE pluggable terminal blocks
Double deck with 2 feed-through circuits - 5.08 mm 0.200 in spacing
2.5 mm²
12 AWG

Description–– Save space with double deck terminal blocks,–– Gain in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– Plug & play connection through pre-wired harnesses equipped with CPFT2 plugs.

Ordering details
1SNC161302F0014

Description
Feed-throughColor
2 feed-through circuits

Type
Grey
Blue

MA2.5/5.D2-2CPE
MA2.5/5.D2-2CPE

Main technical data
1 conductor
per clamp

1SNA400813R0000
1SNA125961R1000

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

UL

CSA

60.5 2.38"

58 2.26"

Weight(1 pce) g

50
50

12.00
12.00

24-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length10 mm
0.394 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

74.5 2.93"

53 2.09"

Pkg
pce

Mounting instructions
IEC

MA2.5/5D-2CPE

Part Number

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

12 A / 2.5 mm² 10 A / 12 AWG
300 A
320 V
300 V
4000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
32.5 1.28"
37.5 1.48"

CE

RoHS

USR CNR

Gost R

5.08 mm 0.200 in spacing

Description
1

2

3

4

5

6

7

8

1
2
3
4

5

9

10

6
7

Color

End stops
10 mm
0.394 inEnd sections
2.54 mm 0.100 in
End section-flange kit (R+L)
Jumper bars
2 poles
24 A
3 poles
4 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
Coding pegs

8

Female plugs
wires parallel

5.08 mm9

Female plugs
5.08 mmwires perpendicular

0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 poles10 Terminal block markers Blank card

Dark grey
Grey
Grey

Grey

Black

Black

White

Type
BAZH1
FEDCP
ENS.FEDBCPBJMI5-2
BJMI5-3
BJMI5-4
BJMI5-10
PC5-2
PC5-10
EL6COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510Part Number
1SNK900102R0000
1SNA400825R0000
1SNA400818R0000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA173627R2100
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
10
10
10
120
80
60
20
120
80
60
20
1

24.00
3.50
11.00
3.30
5.00
6.70
16.90
1.80
6.00
0.10
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

1SNC164005S0201 - Rev. B

Accessories

8MA2.5/5D-2CPE pluggable terminal blocks
Double deck with 1 feed-through circuit - 5.08 mm 0.200 in spacing
2.5 mm²
12 AWG

Description–– Save space with double deck terminal blocks,–– Gain in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– Plug & play connection through pre-wired harnesses equipped with CPFT2 plugs.

Ordering details
1SNC161310F0014

Description
Feed-throughColor
1 feed-through circuit

Type
Grey

MA2.5/5.D-2CPE

1SNA400823R0000

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

UL

CSA

60.5 2.38"

58 2.26"

Weight(1 pce) g

50

12.00

24-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length10 mm
0.394 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

74.5 2.93"

53 2.09"

Pkg
pce

Mounting instructions
IEC

MA2.5/5D-2CPE

Part Number

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

12 A / 2.5 mm² 10 A / 12 AWG
300 A
320 V
300 V
4000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

32.5 1.28"

CE

RoHS

USR CNR

Gost R

37.5 1.48"

5.08 mm 0.200 in spacing

Accessories

8

1

2

3

4

5

6

7

8

10

Type

Part Number

BAZH1
FEDCP
ENS.FEDBCPBJMI5-2
BJMI5-3
BJMI5-4
BJMI5-10
PC5-2
PC5-10
EL6COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510

1SNK900102R0000
1SNA400825R0000
1SNA400818R0000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176282R2300
1SNA113542R1000
1SNA113544R1200
1SNA173627R2100
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Pkg
pce

1
2
3
4

5

9

Color

6
7

End stops
10 mm
0.394 inEnd sections
2.54 mm 0.100 in
End section-flange kit (R+L)
Jumper bars
2 poles
24 A
3 poles
4 poles
10 poles
Lateral jumper bars 2 poles
10 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
Coding pegs

8

Female plugs
wires parallel

5.08 mm9

Female plugs
5.08 mmwires perpendicular

0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 poles10 Terminal block markers Blank card

Dark grey
Grey
Grey

Grey

Black

Black

White

20
20
10
10
10
10
10
10
10
10
10
10
120
80
60
20
120
80
60
20
1

Weight(1 pce) g
24.00
3.50
11.00
3.30
5.00
6.70
16.90
1.80
6.00
0.10
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 181

1SNC164006S0201 - Rev. B

Description

MA2.5/5-SNB-CPE pluggable terminal blocks
Disconnect with blade - 5.08 mm 0.200 in spacing
2.5 mm²

1SNC161303F0014

12 AWG

Description–– Save in flexibility, reliability and simplicity thanks to the pluggable terminal blocks,–– They are particularly well adapted to solve the connecting problems of equipment composed of sub-assemblies (complex machines such as elevators or trains, panel boards with extension boxes...),–– They can then be easily connected through patchcords with CPFT2 plugs connected to the pluggable terminal blocks outputs.

Ordering details
Description
Disconnect

Color
1 feed-through circuit

Type
Grey

Part Number

MA2.5/5-SNB-CPE

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

UL

CSA

63 2.48"60.5 2.38"

55.5 2.19"

50

7.00

24-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length10 mm
0.394 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

58.5 2.30"

26 1.02"

Weight(1 pce) g

Mounting instructions
IEC

MA2.5/5-SNB-CPE

1SNA400815R0000

Pkg
pce

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

10 A / 2.5 mm² 10 A / 12 AWG
120 A
320 V
300 V
4000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

31 1.22"CERoHS

USR CNR

Gost R

5.08 mm 0.200 in spacing

Accessories
Description
1

2

1
2
3

3

4

4
5
6

Color

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 in
Lateral jumper bars 2 poles
30 A
10 polesTest adapters
Test plugs
DIA 2 mm 0.079 in
Coding pegs
End stops

5

6

7

Female plugs
wires parallel

7

8

8

Female plugs
5.08 mmwires perpendicular9

Terminal block markers Blank card

95.08 mm0.200 in 2 poles
3 poles
4 poles
10 poles
0.200 in 2 poles
3 poles
4 poles
10 polesDark grey
Grey
Grey
Blue
Black

Black

Black

White

Type
BAM4
BAZ1
FE2CPE
PC5-2
PC5-10DCB
FC2COCF 32
COC 1
CPFT2/2
CPFT2/3
CPFT2/4
CPFT2/10
CPFT2/R-2
CPFT2/R-3
CPFT2/R-4
CPFT2/R-10
RC510Part Number
1SNK900001R0000
1SNK900002R0000
1SNA400826R0000
1SNA113542R1000
1SNA113544R1200
1SNA105028R2100
1SNA007865R2600
1SNA173660R1600
1SNA299777R1600
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA231000R0700

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
100
10
10
120
80
60
20
120
80
60
20
1

14.00
5.30
2.50
1.80
6.00
20.00
0.10
3.20
4.80
6.40
16.00
3.80
5.70
7.60
19.00
5.20

1SNC164007S0201 - Rev. A

8

D1.5/7.ADO-CPE pluggable terminal blocks
Feed-through ADO - pluggable - 7.62 mm 0.300 in spacing
Description

1.5 mm²–– Disconnect terminal blocks allow easy opening, maintenance and current or voltage testing without disconnecting the wiring,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

16 AWG

1SNC163130F0014

Ordering details
Description

Color

Type

Part Number

pceFeed-through1 ADO, 1 pluggable

Grey

D1.5/7.ADO-CPE

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule

ADO
D1.5/7.ADO-CPE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

44 1.73"36.5 1.44"

1SNA290486R2700

Weight(1 pce) g

50

Mounting instructions
IEC

UL

CSA

0.34-1.5 mm²
0.34-2.5 mm²

22-16 AWGRail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

48.5 1.91"

Pkg

16 A / 1.5 mm² 15 A / 16 AWG
180 A
500 V
300 V
IP20

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
7.62 0.30"

21.8 0.82"

RoHS

USR CNR

Gost R

Notes
7.62 mm 0.300 in spacing

1SSA2662xxR1100

1SSA2672xxR1100

8

1SSA2762xxR1100

Accessories
Description
1

3

5

2

4

6

1

End stops

2

Jumper bars

3
4
5
6

Insulating tips
Locking devices
Coding pegs
Tools

7

Color
10 mm
0.394 in
5.2 mm0.205 in
2 poles
5 poles
10 polesFor jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank card

Dark grey

OrangeBlack
Yellow

White

Type
BAM4
BAZ1
BJE762.2
BJE762.5
BJE762.10
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA290451R0300
1SNA290452R0400
1SNA290453R0500
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
20
10
1
1
50

14.00
5.30
5.30
15.40
24.00
100.000.40
1.00
205.0029.00
6.00
1SNC163075S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

Technical data valid for copper conductors only.

PAGE 183

D2.5/7.ADO-CPE pluggable terminal blocks
Feed-through ADO - pluggable - 7.62 mm 0.300 in spacing
Description

2.5 mm²–– Disconnect terminal blocks allow easy opening, maintenance and current or voltage testing without disconnecting the wiring,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

14 AWG

1SNC163132F0014

Ordering details
Description

Color

Type

Part Number

Feed-through1 ADO, 1 pluggable withblack marking for wire
size 1-2.5 mm²(16-14 AWG)

Grey

D2.5/7.ADO-CPE

Main technical data
D2.5/7.ADO-CPE

Rigid: Solid/Stranded
Flexible without ferrule

ADO
48.5 1.91"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

36.5 1.44"

44 1.73"
7.62 0.30"

1SNA290483R2400

50

Weight(1 pce) g
8.40

Mounting instructions
IEC

UL

CSA

1-2.5 mm²
1-2.5 mm²

16-14 AWGRail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

21.8 0.82"

Pkg
pce

24 A / 2.5 mm² 15 A / 14 AWG
300 A
500 V
300 V
IP20

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

7.62 mm 0.300 in spacing

Notes

8

1SSA2662xxR1100

1SSA2672xxR1100

1SSA2762xxR1100

Description
1

3

5

2

4

6

1

End stops

2

Jumper bars

3
4
5
6

Insulating tips
Locking devices
Coding pegs
Tools

7

Color
10 mm
0.394 in
5.2 mm0.205 in
2 poles
5 poles
10 polesFor jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank card

Dark grey

OrangeBlack
Yellow

White

Type
BAM4
BAZ1
BJE762.2
BJE762.5
BJE762.10
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA290451R0300
1SNA290452R0400
1SNA290453R0500
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
20
10
1
1
50

14.00
5.30
5.30
15.40
24.00
100.000.40
1.00
205.0029.00
6.00

1SNC163077S0201 - Rev. A

Accessories

D1.5/7.2ADO-CPE pluggable terminal blocks
Feed-through ADO - pluggable - 7.62 mm 0.300 in spacing
Description

1.5 mm²–– Disconnect terminal blocks allow easy opening, maintenance and current or voltage testing without disconnecting the wiring,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.
1SNC163131F0014

16 AWG

Ordering details
Description

Color

Type

Part Number

pceFeed-through2 ADO, 1 pluggable

Grey

D1.5/7.2ADO-CPE

Main technical data
D1.5/7.2ADO-CPE

Rigid: Solid/Stranded
Flexible without ferrule

ADO
65.5 2.58"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

36.5 1.44"

44 1.73"
7.62 0.30"

7.62 mm 0.300 in spacing

1SNA290487R2000

Weight(1 pce) g

50

Mounting instructions
IEC

UL

CSA

0.34-1.5 mm²
0.34-2.5 mm²

22-16 AWGRail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

39 1.53"

Pkg

16 A / 1.5 mm² 15 A / 16 AWG
180 A
500 V
300 V
IP20

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Notes

1SSA2662xxR1100

1SSA2672xxR1100

8

1SSA2762xxR1100

Accessories
Description

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8
7

8

10 mm
0.394 in
5.2 mm0.205 in
2.9 mm
0.114 in
2 poles
5 poles
10 polesFor jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank card

Dark grey
Grey

OrangeBlack
Yellow

White

Type
BAM4
BAZ1
FECPE.2ADO
BJE762.2
BJE762.5
BJE762.10
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA291833R1700
1SNA290451R0300
1SNA290452R0400
1SNA290453R0500
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
20
10
1
1
50

14.00
5.30
2.50
5.30
15.40
24.00
100.000.40
1.00
205.0029.00
6.00

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163076S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 185

D2.5/7.2ADO-CPE pluggable terminal blocks
Feed-through ADO - pluggable - 7.62 mm 0.300 in spacing
Description

2.5 mm²–– Disconnect terminal blocks allow easy opening, maintenance and current or voltage testing without disconnecting the wiring,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.
1SNC163133F0014

14 AWG

Ordering details
Description

Color

Type

Part Number

Feed-throughD2.5/7.2ADO-CPE

2 ADO, 1 pluggable withblack marking for wire
size 1-2.5 mm²(16-14 AWG)

Grey

D2.5/7.2ADO-CPE

Main technical data
Rigid: Solid/Stranded
Flexible without ferruleADO
44 1.73"

7.62 mm 0.300 in spacing

7.62 0.30"

39 1.53"36.5 1.44"

65.5 2.58"

Pkg
pce

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

1SNA290484R2500

50

Weight(1 pce) g
11.00

Mounting instructions
IEC

UL

CSA

1-2.5 mm²
1-2.5 mm²

16-14 AWGRail

TH 35-7.5,
TH 35-15

Wire stripping
lengthTool

Screw clamp

24 A / 2.5 mm² 15 A / 14 AWG
300 A
500 V
300 V
IP20

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Notes

8

1SSA2662xxR1100

1SSA2672xxR1100

1SSA2762xxR1100

Description
1

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8
7

8

Color
10 mm
0.394 in
5.2 mm0.205 in
2.9 mm
0.114 in
2 poles
5 poles
10 polesFor jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank card

Dark grey
Grey

OrangeBlack
Yellow

White

Type
BAM4
BAZ1
FECPE.2ADO
BJE762.2
BJE762.5
BJE762.10
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA291833R1700
1SNA290451R0300
1SNA290452R0400
1SNA290453R0500
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
10
20
10
1
1
50

14.00
5.30
2.50
5.30
15.40
24.00
100.000.40
1.00
205.0029.00
6.00

1SNC163078S0201 - Rev. A

Accessories

8

PAGE 187

1SNC160101S0201

9

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Sensors / Actuators
Technologies presentation				190

Overview				

191

Screw clamp technology		
2 wire sensor			
2.5 mm² / 12 AWG

D2.5/6.DP				

192

3 wire sensor			
2.5 mm² / 12 AWG

D2.5/6.DA		
D2.5/6.D		
D2.5/6.DL

With red led

D2.5/6.DAL		 With green led

193
194
195
196

Thermocouple		
MTC6			

197

Spring clamp technology
3 wire sensor			
1.5 mm² / 16 AWG

D2.5/5.C3.L		

198		

D2.5/5.C3.L.L		 With green led

199

4 wire sensor			
1.5 mm² / 16 AWG

D2.5/5.C4.L		

200		

D2.5/5.C4.L.L		 With green led

201

ADO-ADO technology
3 wire sensor			
1 mm² / 20 AWG

D1/5.C3.ADO		

202

D1/5.C3.ADO.L		 With green led

203

4 wire sensor			
D1/5.C4.ADO		

204

D1/5.C4.ADO.L		 With green led

205

9

1SNC160101S0201

1 mm² / 20 AWG

PAGE 189

Dedicated applications terminal blocks
Sensors / Actuators

The smart choice for process
automation applications
Process automation applications typically require the use of alarge number of digital or analog signals and sensors.
The space constraint is often an issue in regards to this large
volume of signals to handle.
TE Connectivity sensor and actuator terminal blocks reduce theinstallation costs, speed the wiring and ease commissioning
thanks to:–– Compact multi deck terminals blocks for 3 & 4 wire sensors–– Potentials distribution via jumper (positive, negative,
ground)–– Signal indication via LED for circuit status indication.

Select from our large choice of solutions and technologies
Classic and compact screw clamp terminal blocks
The product family features very compact dimensions.
It is the preferred choice for small junction boxes when panel
height is a constraints. Our terminals are compatible with:–– 2 wire and 3 wire sensors–– PNP & NPN sensors.

ADO System® terminal blocks: experience the fastest andmost reliable connection on the market
Our exclusive ADO System® combines speed on connection
with top reliability of connection. Our product family offers:–– Compatibility with 2, 3 and 4 wire sensors–– Compatibility with NPN and PNP sensors thanks tobidirectional LED indicators–– Color coded 66 poles plug-in jumpers adapted to all PLC
I/O cards configurations (8,16, 32 & 64 channels).
Universal thermocouple terminal block
This terminal block allows connection of all types oftemperature thermocouple sensors. Its exclusive design allows
thermocouple wire extention with no loss of signal integrity.
Learn more in the related page of our catalog.

Screw clamp terminal block

Spring terminal block

ADO System ® terminal block

Thermocouple terminal block

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

1SNC161167S0201

9

Convenient and ergonomic spring clamp terminal blocks
The product family features popular spring technology
particularly appreciated in process industry.
Our product family offers:–– Compatibility with 2, 3 and 4 wire sensors–– Compatibility with NPN and PNP sensors thanks tobidirectional LED indicators–– Color coded 34 poles plug-in jumpers adapted to popular
PLC I/O cards configurations (8, 16, 32 channels).

Dedicated applications terminal blocks
Sensors / Actuators

Screw clamp technology

2 wire sensor

3 wire sensor

Thermocouple

SectionIEC

UL/CSA

2.5 mm² 12 AWG

D2.5/6.DP

D2.5/6.DA

D2.5/6.D

D2.5/6.DL

D2.5/6.DAL

MTC66 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

Spring clamp technology

3 wire sensor

4 wire sensor

SectionIEC

UL/CSA

1.5 mm² 16 AWG

D2.5/5.C3.L

D2.5/5.C3.L.L

D2.5/5.C4.L

D2.5/5.C4.L.L

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

9

ADO - ADO technology

4 wire sensor

SectionIEC

UL/CSA

1 mm²

20 AWG

D1/5.C3.ADO

D1/5.C3.ADO.L

D1/5.C4.ADO

D1/5.C4.ADO.L

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

PAGE 191

1SNC160063S0201

3 wire sensor

D2.5/6.DP screw clamp terminal blocks
Double deck + ground - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description–– Save space with triple deck terminal blocks: 2 independent circuits in just 6 mm 0.236 in spacing,–– Adapted for 2 wires sensor/actuator with ground.

Ordering details
1SNC161278F0014

Description

Color

Grey,
Feed-through + For 2 wires sensor withgroundground - 2 feed-through Green-Yellow
circuits - 1 groundcircuit

TypePart Number

D2.5/6.DPA1

1SNA115643R2700

Main technical data
1 conductor
per clamp

51 2.01"

58.5 2.30"

81 3.19"36.5 1.44"

Weightqty(1 pce) g

25

16.00

Mounting instructions

Connecting capacity

D2.5/6.DP

Pkg

IEC

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 N.m
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

9

3

5

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

White

Type
BAZH1
FED3E
BJD6

EL61
RC65

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA232000R0000

Pkg

Weightqty(1 pce) g

20
20
10
10
10
10
10
5
10
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
3.60

1SNC161091S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/6.DA screw clamp terminal blocks
Triple deck - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description–– Save space with triple deck terminal blocks: 3 independent circuits connected in just 6 mm 0.236 in spacing,–– Adapted for 3 wires sensor/actuator.

Ordering details

1SNC161154F0014

Description
Feed-throughFor 3 wires sensor- 3 feed-through circuits

Type
Grey

Part Number

D2.5/6.DA

1SNA115541R1100

Main technical data

Pkg

Weightqty(1 pce) g

25

13.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

D2.5/6.DA

Color

IEC

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

51 2.01"

58.5 2.30"

81 3.19"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 N.m
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. for more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

36.5 1.44"
CE

RoHS

USR

CSA

Gost R

6 mm 0.236 in spacing

Accessories
Description

3

5

2

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White

Type
BAZH1
FED3E
BJD6

EL61
RC65

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA232000R0000

Pkg

Weightqty(1 pce) g

20
20
10
10
10
10
10
5
10
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
3.60

9

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161084S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

PAGE 193

D2.5/6.D screw clamp terminal blocks
Sensors / Actuators - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description
Save space with triple deck terminal blocks: adapted for 3 wires sensor/actuator in just 6 mm 0.236 in spacing.

Ordering details
Description

1SNC161093F0014

Sensor51 2.01"

58.5 2.30"

81 3.19"

For 3 wire sensor witha jumper channel oneach deck

Type
Grey

Part Number

D2.5/6.D

1SNA115542R1200

Main technical data

Pkg

Weightpce(1 pce) g

25

10.00

Mounting instructions
IEC

1 conductor
per clamp

D2.5/6.D

Color

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

36.5 1.44"

RoHS

USR

CSA

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

9

3

5

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

White

Type
BAZH1
FED3E
BJD6

EL61
RC65

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
5
10
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
3.60

1SNC161148S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/6.D screw clamp terminal blocks
Sensors / Actuators - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description–– Save space with triple deck terminal blocks: adapted for 3 wires sensor/actuator in just 6 mm 0.236 in
spacing,–– Quickly identify the signal circuit status thanks to the indicator.

Ordering details
1SNC161225F0014

Description
SensorColor
For 3 wire sensor
PNP with red 24 V DC
LED and a jumper bar
channel on middle andlower deck

Type
Grey

Part Number

D2.5/6.DL

1SNA115537R0500

Main technical data

58.5 2.30"
51 2.01"

25

10.00

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

81 3.19"36.5 1.44"

Weight(1 pce) g

Mounting instructions
IEC

D2.5/6.D

1 conductor
per clamp

Pkg
pce

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

6 mm 0.236 in spacing

RoHS

USR

CSA

Gost R

Accessories
Description

3

5

2

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White

Type
BAZH1
FED3E
BJD6

EL61
RC65

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
5
10
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
3.60

9

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161146S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 195D2.5/6.DAL screw clamp terminal blocks
Sensors / Actuators - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description–– Save space with triple deck terminal blocks: 2 independent circuits connected in just 6 mm 0.236 in spacing,–– Adapted for 3 wires sensor/actuator,–– Quickly identify the signal circuit status thanks to the indicator.

Ordering details
1SNC161222F0014

Description
SensorColorPower block with green
LED 24 V DC for 3 wires
sensor and a jumper bar

Type
Grey

Part Number

D2.5/6.DAL2

1SNA115547R1700

Main technical data
1 conductor
per clamp

58.5 2.30"

25

12.00

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

81 3.19"

51 2.01"

Weight(1 pce) g

Mounting instructions
IEC

D2.5/6.DAL

Pkg
pce

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

36.5 1.44"
CE

RoHS

USR

CSA

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

9

3

5

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

White

Type
BAZH1
FED3E
BJD6

EL61
RC65

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
5
10
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
3.60

1SNC161149S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSMTC6 thermocouple terminal blocks
Screw clamp - 6 mm 0.236 in spacing
Description–– Universal terminal block adapted to all type of thermocouples,–– Allow thermocouple wire extention with no loss of signal integrity,–– Compatible with solid type thermocouple wires,–– Reduced inventory: only one part number needed for all configurations.

Ordering details
1SNC161032F0014

Description

Color

Feed-through

TypePart Number

MTC6
MTC6.ExGrey

1SNA115206R2200
1SNA146227R2500

Main technical data

Pkg
pce

Weight(1 pce) g

50
50

20
20

Mounting instructions
NFC

Rail

DIN

2 rigid thermocouple conductors
0.9 to 1.5
500 V
550 V IEC/EN 60079-7 - IM2/M1 II 2 GD/1 GD Ex e I/II

Wire size
MTC6

Rated voltage
Rated voltage Ex e (MTC6.Ex)

Wire stripping
lengthTorqueG32, TH 35-7.5,
TH 35-15
31 mm
1.22 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

44.5 1.75"

48
1.88"

53 2.08"
55.5
2.18"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

Notes
Universal terminal block

length stripped

Other thermocouple terminal blocks are available with hardware(screws, clamps and connecting bar) which match the thermocouple material being used. This requires inventory of manydifferent terminal block types.

31 1.22"

18 0.71"

Wire
insulating

23 0.91"

Iron

Iron

6 mm 0.236 in spacing
MTC 6
Terminal block 1

To temperaturesensing
instrument

Thermocouple

Constantan

Constantan

MTC 6
Terminal block 2

Figure 1: MTC6 with shield connector

1.6 0.06"

lengthstripped

3.3 0.13"

31 1.22"90°

Screw clamp

Principle ofconnection

MTC6 terminal block adapts to all thermocouple material.
This "neutral" method of connection limits the introduction offoreign materials to an insignificant level. The thermocouple wire
insulation is stripped (31 mm maximum) and the bar wires aresuperimposed on each another. The thermocouple wires are incontact over their complete 31 mm length and tightened at two
points by round tip screws (see figure 1). The screws, made ofplated brass, have only a mechanical function, that of holding thewires together with a point contact. Thus, the pressure points
are not relevant in the connection environment. One thermocouple lead connects through one terminal block (see figure 1). The
MTC6 requires only 6 mm of space, allowing 50 terminals perfoot of rail.
Thermocouple shield wire connector bar
The MTC6 can be field or factory equipped with a shield connector bar (see figure 2). This bar, made of treated brass, fits inthe lower part of the terminal block. It ensures the continuity ofthe thermocouple wire shield through the terminal block or to theground with no additional spacing.

9

Figure 2

Description
1

2

Color

Type

Part Number

Pkg
pce

1
2

End sections
2.8 mmShield connectors

0.110 in

Grey

FEM6
CBM5

1SNA118368R1600
1SNA178745R1400

2050

Weight(1 pce) g
2.40

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 197

1SNC161121S0201 - Rev. B

Accessories

D2.5/5.C3.L spring terminal blocks
Sensors / Actuators - 5 mm 0.197 in spacing
Description

1.5 mm²–– Save spacing with 3 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

16 AWG

Ordering details
1SNC162109F0014

Description
SensorColor
3 wiresTypeD2.5/5.C3.L

Grey

1SNA290350R2100

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

UL

56 2.20"

Weight(1 pce) g

50

11.00

0.14-1.5 mm²
0.14-1.5 mm²

CSA

Rail

TH 35-7.5,
TH 35-15

24-16 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.5-1 mm²
A1

79 3.10"48.5 1.91"

Pkg
pce

Mounting instructions
IEC

D2.5/5.C3.LPart Number

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

17.5 A / 1.5 mm²
180 A
300 V
4000 V
IP20
NEMA 1

10 A / 16 AWG
300 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

37.5 1.47"

RoHS

CSA

Gost RNotes
To obtain finger safety (IP20) of a terminal block assembly with comb typejumper bar, it is necessary to put one end section on each side of the terminal
block assembly.

5 mm 0.197 in spacing

Accessories
Description
1

2

9

1
2
3

3

5

4

4

5.2 mm
10 mm
End section kits
5 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 34 poles

End stops

Color
0.205 in
0.394 in
0.197 in
24 A

Type

Dark grey
Grey
Orange

Blue

BAZ1
BAM4
FED5.C3.L
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
PC5.34

Red
Green-yellow

5

Terminal block markers Blank card

White

RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA290358R2500
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA290365R1400
1SNA290366R1500
1SNA290367R1600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
10
10
10
1

5.30
14.00
10.00
1.00
0.70
0.80
0.90
1.20
18.00
18.00
18.00
2.90

1SNC162027S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/5.C3.L spring terminal blocks
Sensors / Actuators - 5 mm 0.197 in spacing
1.5 mm²
16 AWG

Description–– Save spacing with 3 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Quickly identify the circuit status thanks to the indicator.

1SNC162082F0014

Ordering details
Description
SensorColor
3 wires with green bidirectional LED 24 V DC

TypePart Number

D2.5/5.C3.L.L

Grey

1SNA290352R1700

Main technical data
D2.5/5.C3.L

56 2.20"37.5 1.47"

48.5 1.91"

79 3.10"Weight(1 pce) g

50

11.00

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionUL

0.14-1.5 mm²
0.14-1.5 mm²

CSA

Rail

TH 35-7.5,
TH 35-15

24-16 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.5-1 mm²
A1
17.5 A / 1.5 mm²
180 A
300 V
4000 V
IP20
NEMA 1

10 A / 16 AWG
300 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

CSA

Gost R

5 mm 0.197 in spacing

Notes
To obtain finger safety (IP20) of a terminal block assembly with comb typejumper bar, it is necessary to put one end section on each side of the terminal
block assembly.

2

Accessories
Description

3

4

1
2
3

5

4

5.2 mm
10 mm
End section kits
5 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 34 poles
End stops

Color
0.205 in
0.394 in
0.197 in.
24 A

Type

Dark grey
Grey
Orange

Blue

BAZ1
BAM4
FED5.C3.L
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
PC5.34

Red
Green-yellow

5

Terminal block markers Blank card

White

RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA290358R2500
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA290365R1400
1SNA290366R1500
1SNA290367R1600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
10
10
10
1

5.30
14.00
10.00
1.00
0.70
0.80
0.90
1.20
18.00
18.00
18.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

9

1SNC162028S0201 - Rev. A

1

Technical data valid for copper conductors only.

PAGE 199

D2.5/5.C4.L spring terminal blocks
Sensors / Actuators - 5 mm 0.197 in spacing
1.5 mm²
16 AWG

Description–– Save spacing with 4 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation.

1SNC162066F0014

Ordering details
Description
SensorColor
4 wires sensor

TypeD2.5/5.C4.L

Grey

1SNA290354R1100

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

UL

56 2.20"

Weight(1 pce) g

50

13.00

0.14-1.5 mm²
0.14-1.5 mm²

CSA

Rail

TH 35-7.5,
TH 35-15

24-16 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.5-1 mm²
A1

95 3.74"

48.5 1.91"

Pkg
pce

Mounting instructions
IEC

D2.5/5.C4.LPart Number

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

17.5 A / 1.5 mm²
180 A
300 V
4000 V
IP20
NEMA 1

10 A / 16 AWG
300 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

37.5 1.47"

RoHS

5 mm 0.197 in spacing

CSA

Gost RNotes
To obtain finger safety (IP20) of a terminal block assembly with comb typejumper bar, it is necessary to put one end section on each side of the terminal
block assembly.

Accessories
Description
1

2

9

1
2
3

3

4

4

5.2 mm
10 mm
End section kits
5 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 34 poles

End stops

Color
0.205 in
0.394 in
0.197 in
24 A

Type

Dark grey
Grey
Orange

Blue

BAZ1
BAM4
FED5.C4.L
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
PC5.34

Red
Green-yellow

5

Terminal block markers Blank card

White

RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA290360R2300
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA290365R1400
1SNA290366R1500
1SNA290367R1600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
10
10
10
1

5.30
14.00
10.00
1.00
0.70
0.80
0.90
1.20
18.00
18.00
18.00
2.90

1SNC162029S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD2.5/5.C4.L spring terminal blocks
Sensors / Actuators - 5 mm 0.197 in spacing
1.5 mm²
16 AWG

Description–– Save spacing with 4 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Quickly identify the circuit status thanks to the indicator.

1SNC162081F0014

Ordering details
Description
SensorColor
4 wires with bidirectional
green LED 24 V DC

Type
Grey

Part Number

D2.5/5.C4.L.L

1SNA290356R1300

Main technical data

56 2.20"37.5 1.47"

48.5 1.91"

95 3.74"

Weight(1 pce) g

50

13.00

Mounting instructions
IEC

D2.5/5.C4.L

1 conductor
per clamp

Pkg
pce

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionUL

0.14-1.5 mm²
0.14-1.5 mm²

CSA

Rail

TH 35-7.5,
TH 35-15

24-16 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.5-1 mm²
A1
17.5 A / 1.5 mm²
180 A
300 V
4000 V
IP20
NEMA 1

10 A / 16 AWG
300 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

CSA

Gost R

5 mm 0.197 in spacing

Notes
To obtain finger safety (IP20) of a terminal blockassembly with comb type jumper bar, it is necessary
to put one end section on each side of the terminal
block assembly.

1

2

Accessories
3

4

Color

Type

Part Number

BAZ1
BAM4
FED5.C4.L
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
PC5.34

1SNK900002R0000
1SNK900001R0000
1SNA290360R2300
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA290365R1400
1SNA290366R1500
1SNA290367R1600
1SNA230000R1200

Pkg
pce

1
2
3

5

4

5.2 mm
10 mm
End section kits
5 mm
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 34 poles
End stops

0.205 in
0.394 in
0.197 in
24 A

Dark grey
Grey
OrangeBlue
Red
Green-yellow

5

Terminal block markers Blank card

White

RC55

50
50
20
50
50
50
20
20
10
10
10
1

9

Weight(1 pce) g
5.30
14.00
10.00
1.00
0.70
0.80
0.90
1.20
18.00
18.00
18.00
2.90
1SNC162030S0201 - Rev. B

Description

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 201

D1/5.C3.ADO IDC terminal blocks
Sensors / Actuators ADO-ADO - 5 mm 0.197 in spacing
Description

1 mm²–– Save spacing with 3 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires on the upper deck.

20 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163136F0014

pce

SensorFor 3 wire sensor

Grey

D1/5.C3.ADO

1SNA399689R1300

Main technical data

Mounting instructions
IEC

ADO

Rigid: Solid/Stranded
Flexible without ferruleUL

0.2-1 mm²0.22-1 mm²Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

Rail

24-20 AWG

Wire stripping
length69 2.72"

76.5 3.01"

67.3 2.64"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

D1/5.C3.ADO

50

Weight(1 pce) g
9.00

13.5 A / 1 mm²
120 A
250 V
8000 V
IP20
NEMA 1

12 A / 20 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

Notes
47.7 1.87"

5 mm 0.197 in spacing

Description
1

3

2

Color

1

End stops

10 mm
5.2 mm2
3

End section kits
Lateral jumper bars 10 poles

0.394 in
0.205 in

4

Type

Dark grey
Grey
Red

BAM4
BAZ1
FED5.C3.ADO
PC52.10

Blue
Green-yellow

66 polesRed

PC52.66

Blue

5

Green-yellow

45Semi automatic tool
Hand tool
Terminal block markers Blank card

Tools

White

OUPAD
OUMAD
RC55

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399678R2700
1SNA399683R0500
1SNA399684R0600
1SNA399685R0700
1SNA399707R1500
1SNA399708R2600
1SNA399709R2700
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
5
5
5
1
1
1

14.00
5.30
10.00
5.00
5.00
5.00
30.00
30.00
30.00
205.0029.00
2.90
1SNC163044S0201 - Rev. B

Accessories
9

D1/5.C3.ADO IDC terminal blocks
Sensors / Actuators ADO-ADO - 5 mm 0.197 in spacing
Description

1 mm²–– Save spacing with 3 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires on the upper deck.

20 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163125F0014

pce

SensorFor 3 wire sensor withgreen bidirectional
LED 24 VDC

Grey

1SNA399690R1000

Main technical data
ADO

Rigid: Solid/Stranded
Flexible without ferruleUL

0.2-1 mm²0.22-1 mm²Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

Rail

24-20 AWG

Wire stripping
length69 2.72"

76.5 3.01"

13.5 A / 1 mm²
120 A
250 V
8000 V
IP20
NEMA 1

12 A / 20 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

US

cCSAus

RoHS

47.7 1.87"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

67.3 2.64"

50

Mounting instructions
IEC

D1/5.C3.ADO

D1/5.C3.ADO.L

Weight(1 pce) g
10.00

Gost RNotes

5 mm 0.197 in spacing

9

Description
1

3

2

Color

1

End stops

10 mm
5.2 mm2
3

End section kits
Lateral jumper bars 10 poles

0.394 in
0.205 in

4

Type

Dark grey
Grey
Red

BAM4
BAZ1
FED5.C3.ADO
PC52.10

Blue
Green-yellow

66 polesRed

PC52.66

Blue

5

Green-yellow

45Semi automatic tool
Hand tool
Terminal block markers Blank card
Tools

White

OUPAD
OUMAD
RC55

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA399678R2700
1SNA399683R0500
1SNA399684R0600
1SNA399685R0700
1SNA399707R1500
1SNA399708R2600
1SNA399709R2700
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
10
10
10
5
5
5
1
1
1

14.00
5.30
10.00
5.00
5.00
5.00
30.00
30.00
30.00
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 203

1SNC163045S0201 - Rev. B

Accessories

D1/5.C4.ADO IDC terminal blocks
Sensors / Actuators ADO-ADO - 5 mm 0.197 in spacing
Description

1 mm²–– Save spacing with 4 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires on the upper deck.

20 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163137F0014

pce

SensorFor 4 wire sensor

Grey

D1/5.C4.ADO

1SNA399692R0600

Main technical data
Rigid: Solid/Stranded
Flexible without ferruleUL

0.2-1 mm²0.22-1 mm²Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

Rail

24-20 AWG

Wire stripping
length89.2 3.51"

96.7 3.80"

80.1 3.15"

TH 35-7.5,
TH 35-15

Tool

Screw clamp

D1/5.C4.ADO

50

Mounting instructions
IEC

ADO

Weight(1 pce) g

13.5 A / 1 mm²
120 A
250 V
8000 V
IP20
NEMA 1

12 A / 20 AWG
600 V

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

RoHS

US

cCSAusGost R

Notes
47.7 1.87"

5 mm 0.197 in spacing

Accessories
9

Description
1

2

1
2
3

Color

End stops
10 mm
End section kits
Lateral jumper bars 10 poles

0.394 inType

Dark grey
Grey
Red

BAZH1
FED5.C4.ADO
PC52.10

Blue

3

4

Green-yellow

66 polesRed

PC52.66

Blue
Green-yellow

545Semi automatic tool
Hand tool
Terminal block markers Blank card
Tools

White

OUPAD
OUMAD
RC55

Part Number
1SNK900102R0000
1SNA399679R2000
1SNA399683R0500
1SNA399684R0600
1SNA399685R0700
1SNA399707R1500
1SNA399708R2600
1SNA399709R2700
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

20
10
10
10
10
5
5
5
1
1
1

24.00
10.00
5.00
5.00
5.00
30.00
30.00
30.00
205.0029.00
2.90
1SNC163046S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD1/5.C4.ADO IDC terminal blocks
Sensors / Actuators ADO-ADO - 5 mm 0.197 in spacing
Description

1 mm²–– Save spacing with 4 decks terminal block, adapted for sensor/actuator in just 5 mm 0.197 in spacing,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires on the upper deck.

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC163138F0014

pce

SensorFor 4 wire sensor withgreen bidirectional
LED 24 VDC

Grey

1SNA399693R0700

Main technical data
ADO

Rigid: Solid/Stranded
Flexible without ferrule

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

0.2-1 mm²0.22-1 mm²

89.2 3.51"

96.7 3.80"

TH 35-7.5,
TH 35-15

Tool

13.5 A / 1 mm²
120 A
250 V
8000 V
IP20
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

47.7 1.87"

Rail
Wire stripping
lengthScrew clamp

80.1 3.15"

50

Mounting instructions
IEC

D1/5.C4.ADO

D1/5.C4.ADO.L

Weight(1 pce) g

Gost RNotes

5 mm 0.197 in spacing

9

Description
1

2

1
2
3

Color

End stops
10 mm
End section kits
Lateral jumper bars 10 poles

0.394 inType

Dark grey
Grey
Red

BAZH1
FED5.C4.ADO
PC52.10

Blue

3

4

Green-yellow

66 polesRed

PC52.66

Blue
Green-yellow

545Semi automatic tool
Hand tool
Terminal block markers Blank card

Tools

White

OUPAD
OUMAD
RC55

Part Number
1SNK900102R0000
1SNA399679R2000
1SNA399683R0500
1SNA399684R0600
1SNA399685R0700
1SNA399707R1500
1SNA399708R2600
1SNA399709R2700
1SNA178944R0400
1SNA179466R0600
1SNA230000R1200

Pkg

Weightpce(1 pce) g

20
10
10
10
10
5
5
5
1
1
1

24.00
10.00
5.00
5.00
5.00
30.00
30.00
30.00
205.0029.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 205

1SNC163047S0201 - Rev. B

Accessories

1SNC160103S0201

10

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Installation terminal blocks
Technologies presentation			208

Overview				

210

Screw clamp technology		
Multi-level terminal blocks compatible with busbar		
4 mm² / 12 AWG

D4/6.NTLP

Disconnect neutral + feed-through + ground213

D4/6.NLP

Neutral + feed-through + ground214

D4/6.LLP

Feed-through + ground215

D4/6.LL

Feed-through216

Disconnect neutral + feed-through + ground217

Neutral + feed-through + ground219

D4/6.LNTP7

Feed-through + ground221

D4/6.LNTP6

Feed-through223

D4/6.LNTP1 &D4/6.LNTP3
D4/6.LNTP2 &D4/6.LNTP8
D4/6.LNTP4 &Multi-level terminal blocks		
4 mm² / 12 AWG

D4/6.A.NTLP

Disconnect neutral + feed-through + ground224

D4/6.A.LLP

Feed-through + ground

225

Compatible with busbar		
2.5 mm²MA2.5/5.NT

Neutral disconnect

4 mm²

M4/6.NT

Neutral disconnect

226
227

6 mm²

M6/8.NT

Neutral disconnect

228

10 mm²

M10/10.NT

Neutral disconnect229

16 mm²

M16/12.NT

Neutral disconnect

230

35 mm²

M35/16.NT

Neutral disconnect

231

Spring clamp technology
Multi-level terminal blocks compatible with busbar
D2.5/5.NTLP.L

Disconnect neutral + feed-through + ground232

D2.5/5.NLP.L

Neutral + feed-through + ground233

D2.5/5.NL.L

Neutral + feed-through234

D2.5/5.LLP.L

Feed-through + ground235

D2.5/5.LL.L

Feed-through

236

10

1SNC160103S0201

2.5 mm² / 12 AWG

PAGE 207

Dedicated applications terminal blocks
Installation terminal blocks

The preferred choice forbuilding industry
The installation terminal blocks are largely used in distribution
cabinets of public buildings and meet wiring and connection
requirements of installations designed in accordance withDIN VDE 0100 or DIN VDE 0108.
They allow:–– Compact signal distribution thanks to multi-level terminallocks–– Insulation test without disconnecting the neutral conductor thanks to neutral disconnect function on TNS or TNC-S
networks.

Select from our various choice of functions and technologies
Installation terminal blocks
Our product family offer multi-circuit configuration to ease the
distribution of single phase or 3 phase circuits.
Installation terminal blocks are proposed in screw clamp technology.
Various configurations allow distribution of feed-through, neutral,neutral disconnect and ground circuits in a compact format.
Select from our single type terminal blocks or prefer multi-circuitcompact and closed solution combining up to 9 circuits on one
single terminal block.
Neutral bar is aligned with standard single deck terminal blocks
and ensures full compatibility with standard feed-through, neutral
disconnect, or ground terminal blocks.

Multi-level screw clamp terminal
blocksNeutral disconnect: screw clamp
terminal blocks

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Multi-level spring clamp terminal
blocks1SNC161166S0201

10

Neutral disconnect terminal blocks
Neutral disconnect function is mandatory on TNS or TN-C-S
networks used in public buildings and installation complying with
VDE 0108.
Standard specifies:"The distribution must be designed so that it is possible to measure
the insulation resistance of all conductors to ground for each individual outgoing circuit with conductor cross sections up to 10 mm².
This measurement must be performed without disconnecting theneutral conductor. e.g. through the installation of neutral conductor
disconnect terminal blocks."
Our terminals allow simple connection or disconnection of neutral
bar thanks to a sliding link.

Dedicated applications terminal blocks
Installation terminal blocks

3 phase distribution example with installation screw clamp terminal blocks
D4/6.NTLP allows single phase distribution and neutral disconnect
D4/6.LL complement for 3 phase configuration

Transformer

L2

L3

N
PE

Main switch disconnect

L1

D4/6.LL
L1

L2

L2

Secondaryfuses

D4/6.NTLP

N
L3

L3

PE

N
PE

10

1SNC161169S0201

L1

PAGE 209

Dedicated applications terminal blocks
Installation terminal blocks

Screw clamp technology, multi-level terminal blocks compatible with busbar

NTLP

NLP

N

SectionIEC

UL/CSA4 mm²12 AWG

D4/6.NTLP 6 mm 0.236 in

N

IEC

UL/CSA4 mm²12 AWG

D4/6.LLP 6 mm 0.236 in

NLP

LLP

N

N

D4/6.LNTP1

LL

D4/6.NLP 6 mm 0.236 in

NTLP
Section

LLP

N

D4/6.LNTP3

LLN

D4/6.LNTP2

6 mm 0.236 in

D4/6.LL 6 mm 0.236 in

D4/6.LNTP8

6 mm 0.236 in

D4/6.LNTP4

D4/6.LNTP7

6 mm 0.236 in

D4/6.LNTP6
6 mm 0.236 in

Screw clamp technology, multi-level terminal blocks
10

NLP

LLP

LL

N

SectionIEC

UL/CSA4 mm²12 AWG

D4/6.A.NTLP 6 mm 0.236 in

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

D4/6.A.LLP 6 mm 0.236 in

1SNC160102S0201

NTLP

Screw clamp technology, compatible with busbar

Neutral disconnect
Section
2.5 mm4 mm²
6 mm²
10 mm²16 mm²35 mm²GroundN

UL/CSA

12 AWG
8 AWG
6 AWG
0 AWG

MA2.5/5.NT
M4/6.NT
M6/8.NT
M10/10.NT
M16/12.NT
M35/16.NT

5 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 in
10 mm 0.394 in
12 mm 0.472 in
17 mm 0.669 in

MA2.5/5
M4/6
M6/8
M10/10
M16/12
M35/165 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 in
10 mm 0.394 in
12 mm 0.472 in
16 mm 0.630 in

MA2.5/5.P
M4/6.P
M6/8.P
M10/10.P
M16/12.P
M35/16.P

5 mm 0.197 in
6 mm 0.236 in
8 mm 0.315 in
10 mm 0.394 in
12 mm 0.472 in
16 mm 0.630 in

10

1SNC160102S0201

IEC

Feed-through

PAGE 211

Dedicated applications terminal blocks
Installation terminal blocks

Spring clamp technology, multi-level terminal blocks compatible with busbar

NTLP
SectionN

IEC

UL/CSA

2.5 mm²

12 AWG

NLP
N

NL

LLP

LL

N

D2.5/5.NTLP.L

D2.5/5.NLP.L

D2.5/5.NL.L

D2.5/5.LLP.L

D2.5/5.LL.L

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

5 mm 0.197 in

1SNC160102S0201

10

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.NTLP screw clamp terminal blocks
Installation - 6 mm 0.236 in spacing
Description

4 mm²

N

–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161201F0014

pce

Installation

Grey, blue,
Green-yellow

D4/6.NTLPIECUL

1SNA110439R2200

Main technical data
1 conductor
per clamp

D4/6.NTLP

Disconnect neutral +feed-through + ground

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

18-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.8 N.m
3.5 - 7 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Torque51.5 2.03"

59 2.33"

87 3.43"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20

Weight(1 pce) g
20.00

30 A / 4 mm²
480 A
320 V
4000 VIP20

20 A / 12 AWG
Disconnect device
Tool

300 V
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

43.5 1.72"
CE

RoHS

USR CNR

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

7

8

Color

Type

Part Number

Pkg
pce

1
2
3

4
5
6
7
8
9

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Clamps
0.5-35 mm²
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

Grey
Black

White

BAZH1
FED6
BJM62

SCFD
AL2
FC2
SFB1
SFB2
BO3
RC65

1SNK900102R0000
1SNA116964R1200
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA232000R0000

20
20
10
10
10
10
10
10
50
100
50
50
1
1

Weight(1 pce) g
24.00
3.00
2.00
3.00
4.00
5.00
10.00
10.00

12.00
11.00

10

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161064S0201 - Rev. A

9Technical data valid for copper conductors only.

PAGE 213

D4/6.NLP screw clamp terminal blocks
Installation - 6 mm 0.236 in spacing
Description

4 mm²

N

–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details

1SNC161098F0014

Description
Installation

51.5 2.03"

59 2.33"

87 3.43"

Neutral + feed-through+ groundType

Part Number

Grey, blue,
Green-yellow

D4/6.NLPIECUL

1SNA110440R0700

Main technical data
1 conductor
per clamp

D4/6.NLP

Color

Weight(1 pce) g

20

20.00

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg
pce

30 A / 4 mm²
480 A
400 V
6000 V
IP20

CSA

18-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.4 - 0.8 N.m
3.5 - 7 lb.in

20 A / 12 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

43.5 1.72"

RoHS

USR CNR

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

10

1
2
3

4

Dark grey
Grey

White
Grey
Black
White

Type
BAZH1
FED6
BJM62

SCD
SCFD
AL2
FC2
RC65

Part Number
1SNK900102R0000
1SNA116964R1200
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
50
100
1

24.00
3.00
2.00
3.00
4.00
5.00
10.00
1.00
10.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161066S0201 - Rev. A

7

5
6
7

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.LLP screw clamp terminal blocks
Installation - 6 mm 0.236 in spacing
Description

4 mm²–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details

1SNC161097F0014

Description
Installation

2 feed-through + ground

Type

Part Number

Grey,Green-yellow

D4/6.LLP

IEC

UL

1SNA110441R2400

Main technical data
1 conductor
per clamp

D4/6.LLP

Color

Pkg

Weightpce(1 pce) g

20

20.00

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

18-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.4 - 0.8 N.m
3.5 - 7 lb.in

51.5 2.03"

59 2.33"

87 3.43"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

30 A / 4 mm²
480 A
400 V
6000 VIP20

20 A / 12 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

43.5 1.72"

CE

RoHS

USR CNR

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

3

2

1
2
3

4
4

7

6

5
6
7

Dark grey
Grey

White
Grey
Black
White

Type
BAZH1
FED6
BJM62

SCD
SCFD
AL2
FC2
RC65

Part Number
1SNK900102R0000
1SNA116964R1200
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
50
100
1

24.00
3.00
2.00
3.00
4.00
5.00
10.00
1.00
10.00

10

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161070S0201 - Rev. A

5

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

PAGE 215

D4/6.LL screw clamp terminal blocks
Installation - 6 mm 0.236 in spacing
Description

4 mm²–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details

1SNC161203F0014

Description
Installation

59 2.33"

Grey

Part Number

D4/6.LL

1SNA110442R2500

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg

Weightpce(1 pce) g

20

20.00

Mounting instructions
IEC

D4/6.LL

51.5 2.03"

2 feed-throughType

Main technical data
1 conductor
per clamp

87 3.43"

Color

30 A / 4 mm²
480 A
400 V
6000 V
IP20

UL

CSA

18-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.4 - 0.8 N.m
3.5 - 7 lb.in

20 A / 12 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

Gost R

43.5 1.72"

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

10

1
2
3

4

Dark grey
Grey

White
Grey
Black
White

Type
BAZH1
FED6
BJM62

SCD
SCFD
AL2
FC2
RC65

Part Number
1SNK900102R0000
1SNA116964R1200
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
50
100
1

24.00
3.00
2.00
3.00
4.00
5.00
10.00
1.00
10.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161071S0201 - Rev. A

7

5
6
7

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
Description

4 mm²

N

–– Closed terminal block: no end section needed,–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
1SNC161195F0014

Description

Color

Type

Part Number

Installation

3 disconnect neutral+ 3 feed-through+ 3 ground

1SNA110264R0200

D4/6.LNTP1

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

59
2.33"

1 conductor
per clamp

Torque51.5
2.03"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
43.
5 1
87
.72
3.4
"
3"

10

Weight(1 pce) g
70.00

Blue, grey,
green-yellow

Main technical data
D4/6.LNTP

Pkg
pce

30 A / 4 mm²
480 A
320 V
4000 VIP20

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

4

5

6

1

3

8

Part Number

Pkg

4
5
6
7
8

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Clamps
0.5-35 mm²
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card
End stops

Dark grey

BAM4
BAZ1
BJM62

White

SCD
SCFD
AL2
FC2
SFB1
SFB2
BO3
RC65

Grey
Black

White

1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA232000R0000

50
50
10
10
10
10
10
10
10
50
100
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00
10

12.00
11.00
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161072S0201 - Rev. A

7

Type

pce

2
3

Color

Technical data valid for copper conductors only.

PAGE 217

D4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
Description

4 mm²

N

–– Closed terminal block: no end section needed,–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
1SNC161195F0014

Description

Color

Type

Part Number

Installation

1 disconnect neutral+ 3 feed-through+ 1 ground

1SNA110269R1700

D4/6.LNTP3

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

59
2.33"

1 conductor
per clamp

Torque51.5
2.03"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
43.
5 1
87
.72
3.4
"
3"

10

Weight(1 pce) g
70.00

Blue, grey,
green-yellow

Main technical data
D4/6.LNTP

Pkg
pce

30 A / 4 mm²
480 A
320 V
4000 VIP20

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

4

5

6

1

3

10

7

8

Type

Part Number

Pkg
pce

2
3

Color

4
5
6
7
8

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Clamps
0.5-35 mm²
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card
End stops

Dark grey

BAM4
BAZ1
BJM62

White

SCD
SCFD
AL2
FC2
SFB1
SFB2
BO3
RC65

Grey
Black

White

1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA232000R0000

50
50
10
10
10
10
10
10
10
50
100
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00

12.00
11.00
3.60

1SNC161073S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
Description

4 mm²

N

–– Closed terminal block: no end section needed,–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
1SNC161195F0014

Description
Installation

59
2.33"

3 neutral + 3 feed-through + 3 ground

51.5
2.03"

Part Number
1SNA110327R2100

Pkg

Weightpce(1 pce) g

10

70.00

Blue, grey,
Green-yellow

D4/6.LNTP2

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
43.
5 1
87
.72
3.4
"
3"

Type

Main technical data
1 conductor
per clamp

D4/6.LNTP

Color

30 A / 4 mm²
480 A
400 V
6000 VIP20

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

1
2

3

4
3
6

4
5
6

Type

Dark grey

BAM4
BAZ1
BJM62

White

SCD
SCFD
AL2
FC2
RC65

Grey
Black
White

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
100
1

14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00

10

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161074S0201 - Rev. A

5

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 219

D4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
4 mm²

N

12 AWG

Description–– Closed terminal block: no end section needed.
–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

Ordering details
Description
Installation

Color
Blue, Grey,
1 neutral + 3 feed-throughGreen-Yellow+ 1 ground

Type

Part Number

D4/6.LNTP8

1SNA110333R2700

Main technical data
1 conductor
per clamp

51.5
2.03"

10

60.00

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.4 - 0.8 N.m
3.5 - 7 lb.in

59
2.33"

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
43.
5 1
87
.72
3.4
"
3"

Weight(1 pce) g

Mounting instructions
IEC

D4/6.LNTP

Pkg
pce

30 A / 4 mm²
480 A
400 V
6000 VIP20

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

1
2

3

4

5

6

10

3
4
5
6

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops

Color
Dark grey
Grey

White
Grey
Black
White

Type
BAM4
BAZ1
BJM62

SCD
SCFD
AL2
FC2
RC65

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
100
1

14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00
3.60

1SNC161079S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
Description

4 mm²–– Closed terminal block: no end section needed,–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
1SNC161202F0014

Description
Installation

6 feed-through + 3 ground

1SNA110328R0200

Pkg

Weightpce(1 pce) g

10

70.00

Grey,
Green-yellow

D4/6.LNTP4

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

59
2.33"
51.5
2.03"

Part Number

Mounting instructions

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
43.
5 1
87
.72
3.4
"
3"

Type

Main technical data
1 conductor
per clamp

D4/6.LNTP

Color

30 A / 4 mm²
480 A
400 V
6000 VIP20

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

1
2

3

4
3
6

4
5
6

Type

Dark grey

BAM4
BAZ1
BJM62

White

SCD
SCFD
AL2
FC2
RC65

Grey
Black
White

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
100
1

14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00

10

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161080S0201 - Rev. A

5

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 221D4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
Description

4 mm²–– Closed terminal block: no end section needed,–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
1SNC161202F0014

Description
Installation

Color
6 feed-through + 1 ground

Weight(1 pce) g

10

60.00

Grey,
Green-yellow

D4/6.LNTP7

IEC

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.4 - 0.8 N.m
3.5 - 7 lb.in

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

59
2.33"
51.5
2.03"

1SNA110332R2600

Pkg
pce

Mounting instructions

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
43.
5 1
87
.72
3.4
"
3"

Part Number

Main technical data
1 conductor
per clamp

D4/6.LNTP

Type

30 A / 4 mm²
480 A
400 V
6000 VIP20

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

1
2

3

4

5

6

10

3
4
5
6

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops

Color

Type

Dark grey

BAM4
BAZ1
BJM62

White

SCD
SCFD
AL2
FC2
RC65

Grey
Black
White

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
100
1

14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00
3.60

1SNC161082S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.LNTP screw clamp terminal blocks
Installation - 17.8 mm 0.701 in spacing
Description

4 mm²–– Closed terminal block: no end section needed,–– According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm),–– Compatible with busbar.

12 AWG

Ordering details
1SNC161202F0014

Description
Installation

59
2.33"

6 feed-through

GreyPart Number

D4/6.LNTP6

1SNA110331R2500

Pkg

Weightpce(1 pce) g

10

63.10

Mounting instructions
IEC

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

51.5
2.03"

Type

Main technical data
1 conductor
per clamp

D4/6.LNTP

Color

30 A / 4 mm²
480 A
400 V
6000 V
IP20

UL

CSA

Rail

TH 35-7.5,
TH 35-15

18-12 AWG

18-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.4 - 0.8 N.m
3.5 - 7 lb.in

20 A / 12 AWG 20 A / 12 AWG
300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when apply) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
43.
5 1
87
.72
3.4
"
3"

CE

RoHS

USR CNR

CSA

Gost R

17.8 mm 0.701 in spacing

Accessories
Description
1

2

1
2

3

4
3
6

4
5
6

Type

Dark grey

BAM4
BAZ1
BJM62

White

SCD
SCFD
AL2
FC2
RC65

Grey
Black
White

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
50
10
10
10
10
10
10
10
50
100
1

14.00
5.30
2.00
3.00
4.00
5.00
10.00
1.00
10.00

10

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161083S0201 - Rev. A

5

10 mm
0.394 in
5.2 mm0.205 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops

Color

Technical data valid for copper conductors only.

PAGE 223

D4/6.A.NTLP screw clamp terminal blocks
Installation - 6 mm 0.236 in spacing
Description

4 mm²

N

According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm).

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161139F0014

Installation

Disconnect neutral +feed-through + ground

Grey, blue,
Green-yellow

D4/6.A.NTLP

IEC

UL

1SNA110415R1200

Main technical data
1 conductor
per clamp

D4/6.A.NTLP

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

59 2.33"
51.5 2.03"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

10

Mounting instructions
CSA

18-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.8 Nm
3.5 - 7 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Torque90 3.55"

Weight(1 pce) g

30 A / 4 mm²
480 A
320 V
4000 VIP20

20 A / 12 AWG
Disconnect device
Tool

300 V
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

43.5 1.72"

CE

RoHS

USR CNR

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

Part Number

Pkg

1
2
3

5
6
7

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White
Grey
Black
White

BAZH1
FEDA6
BJM62

SCD
SCFD
AL2
FC2
RC65

1SNK900102R0000
1SNA116965R1300
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

20
20
10
10
10
10
10
10
10
50
100
1

Weight(1 pce) g
24.00
3.00
2.00
3.00
4.00
5.00
10.00
1.00
10.00

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161128S0201 - Rev. B

7

Type

pce

4

10

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/6.A.LL screw clamp terminal blocks
Installation - 6 mm 0.236 in spacing
Description

4 mm²

According to DIN 43880 standards (dimension above the rail 35 x 7.5 ≤ 44 mm).

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161280F0014

Installation

2 feed-through + ground

Grey, Greenyellow

D4/6.A.LLP

IEC

UL

1SNA110418R2500

Main technical data
1 conductor
per clamp

D4/6.A.LL

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

18-12 AWG

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.8 Nm
3.5 - 7 lb.in

Torque51.5 2.03"

59 2.33"

90 3.55"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20

Weight(1 pce) g
20.00

30 A / 4 mm²
480 A
400 V
6000 VIP20

20 A / 12 AWG
Disconnect device
Tool

300 V
NEMA 1Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

43.5 1.72"

RoHS

USR CNR

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

Type

Part Number

Pkg
pce

1
2
3

4
5
6
7

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
0 in
1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White
Grey
Black
White

BAZH1
FEDA6
BJM62

SCD
SCFD
AL2
FC2
RC65

1SNK900102R0000
1SNA116965R1300
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA103189R2600
1SNA114117R0700
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

20
20
10
10
10
10
10
10
10
50
100
1

Weight(1 pce) g
24.00
3.60
2.00
3.00
4.00
5.00
10.00
1.00
10.00
10

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161129S0201 - Rev. A

7

Color

Technical data valid for copper conductors only.

PAGE 225

MA2.5/5.NT screw clamp terminal blocks
Neutral disconnect - 5 mm 0.197 in spacing
2.5 mm²

N

Description–– Ease the disconnection of your neutral circuits,–– Compatible with screw clamp terminal blocks, wire size 2.5 mm² (5 mm 0.200 in spacing) to 16 mm²(12 mm 0.473 in spacing).

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161075F0014

pce

Neutraldisconnect

For busbar 10 x 3 mm

Blue

MA2.5/5.NT

1SNA125487R0600

Main technical data

Mounting instructions
IEC

1 conductor
per clamp
MA2.5/5.NT

UL

CSA

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length10 mm
0.39 inScrew clamp
Tool

Flat screwdriverØ 3.5 mm
Ø 0.14 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Torque55.5 2.18"
48 1.89"

53 2.09"H

54.5 2.15"

50Weight(1 pce) g
12.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A
400 V
6000 V

Disconnect device
Tool
NEMA

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. for more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

18 0.71"
23 0.91"

5 mm 0.197 in spacing

Accessories
Description
1

3

5

1

End stops

4

2
3
4
5
6

End sections
Test adapters
Test plugs
Locking devices
Clamps10

TypePart Number

Pkg
pce

2

6

Color

7
8

10 mm
5.2 mm
2.8 mm

0.394 in
0.205 in
0.110 in

DIA 2 mm 0.079 in
For busbar BO3
0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card

Dark grey
Grey
Green
Black
Blue

White

BAM4
BAZ1
FEM6
DCV
FC2
VRB3
SFB1
SFB2
BO3
RC510

1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA173058R0200
1SNA007865R2600
1SNA128035R1600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA231000R0700

50
50
20
10
100
10
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.40
2.20

12.00
11.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

8

1SNC161086S0201 - Rev. A

7

Technical data valid for copper conductors only

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.NT screw clamp terminal blocks
Neutral disconnect - 6 mm 0.236 in spacing
4 mm²

N

12 AWG

Description–– Ease the disconnection of your neutral circuits,–– Compatible with screw clamp terminal blocks, wire size 2.5 mm² (5 mm 0.200 in spacing) to 16 mm²(12 mm 0.473 in spacing).

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161079F0014

pce

Neutraldisconnect

For busbar 10 x 3 mm

Blue

M4/6.NT

1SNA125117R0200

Main technical data

Mounting instructions
IEC

1 conductor
per clamp
M4/6.NTUL

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

Rail

G32, TH 35-7.5,
TH 35-15

18-12 AWG

Wire stripping
length

12 mm
0.47 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Torque55.5 2.18"
48 1.89"

53 2.09"H

54.5 2.15"

50Weight(1 pce) g
13.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

32 A / 4 mm²
480 A
400 V
6000 V

25 A / 12 AWG
300 V
NEMA

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

CSA

Gost R

18 0.71"
23 0.91"

6 mm 0.236 in spacing

Accessories
Description
1

3

5

Type

Part Number

Pkg
pce

2

1

End stops

4

2
3
4
5
6

End sections
Test adapters
Test plugs
Locking devices
Clamps

6

Color

7
8

10 mm
5.2 mm
2.8 mm

0.394 in
0.205 in
0.110 in

DIA 2 mm 0.079 in
For busbar BO3
0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card

Dark grey
Grey
Green
Black
Blue

White

BAM4
BAZ1
FEM6
DCV
FC2
VRB3
SFB1
SFB2
BO3
RC610

1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA173058R0200
1SNA007865R2600
1SNA128035R1600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA233000R0100

50
50
20
10
100
10
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.40
2.20

12.00
11.00
7.50
10

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

8

1SNC161087S0201 - Rev. A

7

Technical data valid for copper conductors only.

PAGE 227

M6/8.NT screw clamp terminal blocks
Neutral disconnect - 8 mm 0.315 in spacing
6 mm²

N

8 AWG

Description–– Ease the disconnection of your neutral circuits,–– Compatible with screw clamp terminal blocks, wire size 2.5 mm² (5 mm 0.200 in spacing) to 16 mm² (12 mm
0.473 in spacing).

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161080F0014

pce

Neutraldisconnect

For busbar 10 x 3 mm

Blue

M6/8.NT

1SNA125119R1400

Main technical data

Mounting instructions
IEC

1 conductor
per clamp
M6/8.NTUL

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

CSA

Rail

G32, TH 35-7.5,
TH 35-15

18-8 AWG

Wire stripping
length

12 mm
0.47 inScrew clamp
Tool

Flat screwdriverØ 4-5 mm
Ø 0.16-0.20 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Torque55.5 2.18"
48 1.89"

53 2.09"H

54.5 2.15"

50Weight(1 pce) g
17.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

41 A / 6 mm²
720 A
400 V
6000 V

50 A / 8 AWG
300 V
NEMA

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. for more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

CSA

Gost R

18 0.71"
23 0.91"

8 mm 0.315 in spacing

Accessories
Description
1

2

3

4

5

6

10

Color

Type

Part Number

Pkg
pce

1
2
3
4
5
6
7

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 in
Test plugs
DIA 2 mm 0.079 in
Locking devices For busbar BO3
Clamps
0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card
End stops

Dark grey
Grey
Black
Blue

White

BAM4
BAZ1
FEM6
FC2
VRB3
SFB1
SFB2
BO3
RC810

1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA007865R2600
1SNA128035R1600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA234000R0200

50
50
20
100
10
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.40

12.00
11.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161088S0201 - Rev. A

7

Technical data valid for copper conductors only

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM10/10.NT screw clamp terminal blocks
Neutral disconnect - 10 mm 0.394 in spacing
10 mm²N

6 AWG

Description–– Ease the disconnection of your neutral circuits,–– Compatible with screw clamp terminal blocks, wire size 2.5 mm² (5 mm 0.200 in spacing) to 16 mm² (12 mm
0.473 in spacing).

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161081F0014

pce

Neutraldisconnect

For busbar 10 x 3 mm

Blue

M10/10.NT

1SNA125121R0600

Main technical data

Mounting instructions
IEC

1 conductor
per clamp
M10/10.NT

UL

Rigid: Solid/Stranded
0.5-16 mm²
Flexible without ferrule
0.5-10 mm²
Flexible with insulated ferrule
Gauge
B6

CSA

Rail

G32, TH 35-7.5,
TH 35-15

18-6 AWG

Wire stripping
length

12 mm
0.47 inScrew clamp
Tool

Flat screwdriverØ 5.5-6 mm
Ø 0.22-0.24 in
1.2 - 1.4 N.m
10.6 - 12.3 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

Torque55.5 2.18"
48 1.89"

53 2.09"H

54.5 2.15"

50Weight(1 pce) g
19.00

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

57 A / 10 mm²1200 A
400 V
6000 V

75 A / 6 AWG
300 V
NEMA

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

CSA

Gost R

18 0.71"
23 0.91"

10 mm 0.394 in spacing

Accessories
Description
1

3

2

1

4

2
3
4

Part Number

Pkg

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inLocking devices For busbar BO3
Clamps
0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card
End stops

Dark grey
Grey
Blue

White

BAM4
BAZ1
FEM6
VRB3
SFB1
SFB2
BO3
RC1010

1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA128035R1600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA238000R1600

50
50
20
10
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.40
12.00
11.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

10

1SNC161089S0201 - Rev. A

6

Type

pce

5
6
5

Color

Technical data valid for copper conductors only

PAGE 229

M16/12.NT screw clamp terminal blocks
Neutral disconnect - 12 mm 0.472 in spacing
16 mm²N

Description–– Ease the disconnection of your neutral circuits,–– Compatible with screw clamp terminal blocks, wire size 2.5 mm² (5 mm 0.200 in spacing) to 16 mm² (12 mm
0.473 in spacing).

Ordering details
Description

Color

Type

Part Number

Pkg

1SNC161074F0014

pce

Neutraldisconnect

For busbar 10 x 3 mmBlue

M16/12.NT1

1SNA125593R0000

Main technical data

Mounting instructions
IEC

1 conductor
per clamp
M16/12.NT

UL

CSA

Rigid: Solid/Stranded
2.5-25 mm²
Flexible without ferrule
2.5-16 mm²
Flexible with insulated ferrule
Gauge
B7

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length14 mm
0.51 inScrew clamp
Tool

Flat screwdriverØ 5.5 mm
Ø 0.22 in
1.2 - 1.4 N.m
10.6 - 12.3 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Torque55.5 2.18"
48 1.89"

53 2.09"H

54 2.13"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20

Weight(1 pce) g
26.00

76 A / 16 mm²
1920 A
400 V
6000 V

Disconnect device
Tool
NEMA

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. for more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

19 0.75"
24 0.95"

12 mm 0.472 in spacing

Accessories
Description
1

2

5

6

Part Number

Pkg

1

4
5
6

10 mm
0.394 in
5.2 mm0.205 inEnd sections
2.8 mm0.110 inLocking devices For busbar BO3
For busbar BO6
Clamps
0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG
Busbars
Busbars
Terminal block markers Blank card
End stops

Dark grey
Grey
Blue

White

BAM4
BAZ1
FEM6
VRB3
VRB6
SFB1
SFB2
BO3
RC1010

1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA128035R1600
1SNA128361R0100
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA238000R1600

50
50
20
10
20
50
50
1
1

Weight(1 pce) g
14.00
5.30
2.40

12.00
11.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161090S0201 - Rev. A

10

4

Type

pce

2
3
3

Color

Technical data valid for copper conductors only

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM35/16.NT screw clamp terminal blocks
Neutral disconnect - 17 mm 0.669 in spacing
Description

35 mm²N–– Ease the disconnection of your neutral circuits,–– Close terminal block, no end section needed,–– Compatible with screw clamp terminal blocks, wire size 2.5 mm² (5 mm 0.200 in spacing) to 16 mm² (12 mm
0.473 in spacing).

0 AWG

Ordering details
1SNC161308F0014

Description

Color

Type

Neutraldisconnect

For busbar 10 x 3 mmBlue

M35/16.NT

1SNA125358R0300

Main technical data
1 conductor
per clamp

CSA

Rigid: Solid/Stranded
10-50 mm²
Flexible without ferrule
10-35 mm²
Flexible with insulated ferrule
Gauge
B9

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length17 mm
0.67 inScrew clamp
Tool

Flat screwdriverØ 6.5-7 mm
Ø 0.256 - 0.276 in
2.8 - 3 Nm
24.6 - 26.1 lb.in
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

H
61.5 2.42"

125 A / 35 mm²4200 A
400 V
6000 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

54 2.13"59 2.32"20

Weight(1 pce) g
60.00

Mounting instructions
UL

Torque58.5 2.30"

Pkg
pce

IEC

M35/16.NTPart Number

22 0.87"

CE

RoHS

Disconnect device
Tool
NEMA

TorqueGost R

27 1.06"

17 mm 0.669 in spacing

Accessories
Description

3

5

2

4

Type

Part Number

Pkg
pce

1

End stops

10 mm
0.394 in
5.2 mm0.205 inFor busbar BO3
0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG

2
3

Locking devices
Clamps4
5

Busbars
Terminal block markers Blank card

Dark grey
Blue

White

BAM4
BAZ1
VRB3
SFB1
SFB2
BO3
RC1010

1SNK900001R0000
1SNK900002R0000
1SNA128035R1600
1SNA163860R0500
1SNA168956R0600
1SNA164406R2400
1SNA238000R1600

50
50
10
50
50
1
1

Weight(1 pce) g
14.00
5.30
12.00
11.00
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

10

1SNC161156S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 231D2.5/5.NTLP.L spring terminal blocks
Installation - 5 mm 0.197 in spacing
2.5 mm²

N

1SNC162069F0014

12 AWG

Description–– Specially developped for TN-C-S Network,–– Easy disconnection of neutral for isolation,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Save space with compact angled terminal blocks.

Ordering details
Description
Installation

D2.5/5.NTLP.L

Color
Disconnect neutral withbusbar connection +feed-through + groundcircuits

TypePart Number

Grey, blue,
green-yellow

D2.5/5.NTLP.L

IEC

UL

0.14-4 mm²
0.14-2.5 mm²

26-12 AWG

1SNA290322R0100

Main technical data

47 1.85"54.5 2.14"

107 4.21"

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Pkg

Weightpce(1 pce) g

40

15.00

Mounting instructions
CSA

0.5-2.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

53.5 2.11"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
5 mm 0.197 in spacing

20 A / 2.5 mm² 20 A / 12 AWG
300 A
250 V
300 V
4000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

Accessories
Description
1

3

4

5

6

7

1

End stops

Dark grey

4

Clamps

5.2 mm0.205 in
10 mm
0.394 in
2.5 mm
0.098 in
2 poles
24 A
3 poles
4 poles
5 poles
10 poles0.5-35 mm² 18-2 AWG
16-35 mm² 6-2 AWG

23

End sections
Jumper bars

5
6

Distribution bar holders
Busbars
1000 x 10 x 3 mm
39.4 x 0.394 x 0.118 inTerminal block markers Blank card

Blue

7

Grey
Orange

White

Type

Part Number

Pkg

Weightpce(1 pce) g

BAZ1
BAM4
FED5.L.A
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
SFB1
SFB2
SPBO.NT.L
BO3

1SNK900002R0000
1SNK900001R0000
1SNA291559R0400
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA163860R0500
1SNA168956R0600
1SNA399886R2100
1SNA164406R2400

50
50
20
50
50
50
20
20
50
50
20
1

5.30
14.00
5.50
1.00
0.70
0.80
0.90
1.20
12.00
11.00
12.00

RC55

1SNA230000R1200

1

2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Installation spring terminal blocks
Description
Installation

Color
2 feed-through circuits

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Type
Grey

D2.5/5.LL.LPart Number
1SNA290328R1700

Pkg

Weightpce(1 pce) g

40

13.00

1SNC162038S0201 - Rev. A

10

2

Color

D2.5/5.NLP.L spring terminal blocks
Installation - 5 mm 0.197 in spacing
2.5 mm²

N

1SNC162068F0014

12 AWG

D2.5/5.NLP.L

Description–– Specially developped for TN-C-S Network,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Save space with compact angled terminal blocks.

Ordering details
Description
Installation

Color
Neutral + feed-through + ground circuits

TypePart Number

Grey, blue,
Green-yellow

D2.5/5.NLP.L

IEC

UL

0.14-4 mm²
0.14-2.5 mm²

26-12 AWG

1SNA290324R0300

Main technical data
1 conductor
per clamp

53.5 2.11"

47 1.85"54.5 2.14"

107 4.21"

Pkg

Weightpce(1 pce) g

40

17.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

0.5-2.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 20 A / 12 AWG
300 A
250 V
300 V
4000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5 mm 0.197 in spacingRoHS

USR CNR

Gost R

Accessories
Description

3

5

2

1

End stops2
3

End sections
Jumper bars

45

Distribution bar holders
Terminal block markers Blank card

4

5.2 mm
10 mm
2.5 mm2 poles
3 poles
4 poles
5 poles
10 poles

0.205 in
0.394 in
0.098 in
24 A

Dark grey
Grey
Orange

Blue
White

Type
BAZ1
BAM4
FED5.L.B
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
SPBO.NT.L
RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA291560R0100
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA399886R2100
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
20
1

5.30
14.00
5.50
1.00
0.70
0.80
0.90
1.20
12.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

10

Installation spring terminal blocks
Description
Installation

Color
2 feed-through circuits

Type
Grey

D2.5/5.LL.LPart Number
1SNA290328R1700

Pkg

Weightpce(1 pce) g

40

13.00

Technical data valid for copper conductors only.

PAGE 233

1SNC162039S0201 - Rev. A

1

Color

D2.5/5.NL.L spring terminal blocks
Installation - 5 mm 0.197 in spacing
2.5 mm²

N

1SNC162096F0014

12 AWG

Description–– Specially developped for TN-C-S Network,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Save space with compact angled terminal blocks.

Ordering details
Description
Installation

Color
Neutral + feed-through circuits

TypePart Number

D2.5/5.NL.L

Grey, blue

1SNA290330R1500

Main technical data

53.5 2.11"

47 1.85"54.5 2.14"

107 4.21"

Weight(1 pce) g

40

13.00

Mounting instructions

D2.5/5.NL.L

1 conductor
per clamp

Pkg
pce

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.14-4 mm²
0.14-2.5 mm²

26-12 AWG

0.5-2.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 20 A / 12 AWG
300 A
400 V
300 V
6000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

5 mm 0.197 in spacing

Accessories
Description
1

3

5

2

Color

1

End stops2
3

End sections
Jumper bars

45

Distribution bar holders
Terminal block markers Blank card

4

5.2 mm
10 mm
2.5 mm2 poles
3 poles
4 poles
5 poles
10 poles

0.205 in
0.394 in
0.098 in
24 A

Dark grey
Grey
Orange

Blue
White

Type
BAZ1
BAM4
FED5.L.B
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
SPBO.NT.L
RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA291560R0100
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA399886R2100
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
20
1

5.30
14.00
5.50
1.00
0.70
0.80
0.90
1.20
12.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Installation spring terminal blocks
Description
Installation

Color
2 feed-through + ground circuits

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Grey, green-yellow

TypeD2.5/5.LLP.LPart Number
1SNA290326R0500

Pkg

Weightpce(1 pce) g

40

17.00

1SNC162041S0201 - Rev. A

10

D2.5/5.LLP.L spring terminal blocks
Installation - 5 mm 0.197 in spacing
2.5 mm²

1SNC162067F0014

12 AWG

D2.5/5.LLP.L

Description–– Specially developped for TN-C-S Network,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Save space with compact angled terminal blocks.

Ordering details
Description
Installation

Color
2 feed-through + ground circuits

TypePart Number

Grey,Green-yellow

D2.5/5.LLP.L

IEC

UL

0.14-4 mm²
0.14-2.5 mm²

26-12 AWG

1SNA290326R0500

Main technical data
1 conductor
per clamp

53.5 2.11"

47 1.85"54.5 2.14"

107 4.21"

Pkg

Weightpce(1 pce) g

40

17.00

Mounting instructions

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

0.5-2.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 20 A / 12 AWG
300 A
250 V
300 V
4000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5 mm 0.197 in spacingRoHS

USR CNR

Gost R

Accessories
Description
1

2

3

1

End stops2
3

End sections
Jumper bars

45

Distribution bar holders
Terminal block markers Blank card

4

5

Color
5.2 mm
10 mm
2.5 mm2 poles
3 poles
4 poles
5 poles
10 poles

0.205 in
0.394 in
0.098 in
24 A

Dark grey
Grey
Orange

Blue
White

Type
BAZ1
BAM4
FED5.L.B
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
SPBO.NT.L
RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA291560R0100
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA399886R2100
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
20
1

5.30
14.00
5.50
1.00
0.70
0.80
0.90
1.20
12.00
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

N

Installation spring terminal blocks
Description
Installation

Color
Neutral + feed-through circuits

Grey, blueTypeD2.5/5.NL.LPart Number
1SNA290330R1500

Pkg

Weightpce(1 pce) g

40

13.00

Technical data valid for copper conductors only.

PAGE 235

1SNC162040S0201 - Rev. A

10

D2.5/5.LL.L spring terminal blocks
Installation - 5 mm 0.197 in spacing
2.5 mm²

1SNC162097F0014

12 AWG

Description–– Specially developped for TN-C-S Network,–– Easy to access thanks to the front wiring entry,–– Clamping contact pressure non dependent on the operator and automatic creeping compensation,–– Save space with compact angled terminal blocks.

Ordering details
Description
Installation

Color
2 feed-through circuits

Type
Grey

Part Number

D2.5/5.LL.L

1SNA290328R1700

Main technical data

53.5 2.11"

47 1.85"54.5 2.14"

107 4.21"

Weight(1 pce) g

40

13.00

Mounting instructions

D2.5/5.LL.L

1 conductor
per clamp

Pkg
pce

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

IEC

UL

CSA

0.14-4 mm²
0.14-2.5 mm²

26-12 AWG

0.5-2.5 mm²
A2

Rail

TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 20 A / 12 AWG
300 A
400 V
300 V
6000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

5 mm 0.197 in spacing

Accessories
Description
1

3

2

1

End stops2
3

End sections
Jumper bars

45

Distribution bar holders
Terminal block markers Blank card

4

10

5

Color
5.2 mm
10 mm
2.5 mm2 poles
3 poles
4 poles
5 poles
10 poles

0.205 in
0.394 in
0.098 in
24 A

Dark grey
Grey
Orange

Blue
White

Type
BAZ1
BAM4
FED5.L.B
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
SPBO.NT.L
RC55

Part Number
1SNK900002R0000
1SNK900001R0000
1SNA291560R0100
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA399886R2100
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
50
20
50
50
50
20
20
20
1

5.30
14.00
4.75
1.00
0.70
0.80
0.90
1.20
12.00
2.90

1SNC162042S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Protection
Overview					

238Screw clamp technology		
Ground + neutral		
10 mm²

M10/10.PE.N		

239

16 mm²

M16/12.PE.N		

240

35 mm²

M35/16.PE.N		

241

1SNC160104S0201

11

PAGE 237

Dedicated applications terminal blocks
Protection

Screw clamp technology

PEN
SectionIEC

10 mm²16 mm²35 mm²Feed-throughN

UL/CSA

M10/10.PE.N 20 mm 0.787 in
M16/12.PE.N 24 mm 0.945 in
M35/16.PE.N 32 mm 1.260 in

M10/10 10 mm 0.394 in
M16/12 12 mm 0.472 in
M35/16 16 mm 0.630 in

1SNC160097S0201

11

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM10/10.PE.N screw clamp terminal blocks
Ground + neutral - 20 mm 0.787 in spacing
10 mm²N

Description–– Simplify your PE.N connection with M10/10.P block connected to M10/10.N block through a pre-mounted
jumper,–– Adapted to TNS and TNC-S electrical network.

Ordering details

1SNC161177F0014

Description
Ground+ neutral

Color
Screw rail connection

TypePart Number

Green-yellow,
blue

M10/10.PE.N

IEC

UL

1SNA165683R2200

Main technical data
1 conductor
per clamp

M10/10.PE.N

CSA

Rigid: Solid/Stranded
0.5-16 mm²
Flexible without ferrule
0.5-10 mm²
Flexible with insulated ferrule
Gauge
B6

Rail
Wire stripping
lengthScrew clamp
Tool
Torque10 mm²1200 A

Rail connection screw
Tool

55.5
2.18"

53 2.09"48
1.89"

Weight(1 pce) g

20

53.00

Mounting instructions

Rated cross section
Rated short-time withstand current (1s)44.5 1.75"

Pkg
pce

TorqueG32, TH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 5.5 mm
Ø 0.22 in
1.2 - 1.4 N.m
10.6 - 12.3 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.8 N.m
7.1 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

18 0.71"
23 0.91"

CE

RoHS

Gost R

20 mm 0.787 in spacing

Accessories
Description
2

1
2

10 mm
5.2 mmCircuit separators 2.4 mm

0.394 in
0.205 in0.094 in

3 mm

0.118 inEnd stops

Dark grey
Grey

Type
BAM4
BAZ1
SCFEX1SCFEX3SCFM6Part Number
1SNK900001R0000
1SNK900002R0000
1SNA103619R0400
1SNA103620R0100
1SNA114825R0500

Pkg

Weightpce(1 pce) g

50
50
10
10
20

14.00
5.30
30.00
30.00
4.00

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

11

1SNC161014S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 239

M16/12.PE.N screw clamp terminal blocks
Ground + neutral - 24 mm 0.945 in spacing
16 mm²N

Description–– Simplify your PE.N connection with M16/12.P block connected to M16/12.N block through a pre-mounted
jumper,–– Adapted to TNS and TNC-S electrical network.

Ordering details

1SNC161176F0014

Description
Ground+ neutral

Color
Screw rail connection

TypePart Number

Green-yellow,
blue

M16/12.PE.N

IEC

UL

1SNA165680R0300

Main technical data
1 conductor
per clamp

M16/12.PE.N

CSA

Rigid: Solid/Stranded
2.5-25 mm²
Flexible without ferrule
2.5-16 mm²
Flexible with insulated ferrule
Gauge
B7

Rail
Wire stripping
lengthScrew clamp
Tool
Torque

16 mm²1920 A

Rail connection screw
Tool

55.5
2.18"

53 2.09"48
1.89"

Weight(1 pce) g

20

68.00

Mounting instructions

Rated cross section
Rated short-time withstand current (1s)

49 1.93"

Pkg
pce

TorqueG32, TH 35-7.5,
TH 35-15
14 mm
0.55 inFlat screwdriverØ 5.5 mm
Ø 0.22 in
1.2 - 1.4 N.m
10.6 - 12.3 lb.in
Flat screwdriverØ 5.5 mm
Ø 0.22 in
1 N.m
8.8 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

22 0.87"
27 1.06"

CE

RoHS

Gost R

24 mm 0.945 in spacing

Accessories
Description
1

2

1
2

Color

10 mm
5.2 mmCircuit separators 2.4 mm

0.394 in
0.205 in0.094 in

3 mm

0.118 inEnd stops

Dark grey
Grey

Type
BAM4
BAZ1
SCFEX1SCFEX3SCFM6Part Number
1SNK900001R0000
1SNK900002R0000
1SNA103619R0400
1SNA103620R0100
1SNA114825R0500

Pkg

Weightpce(1 pce) g

50
50
10
10
20

14.00
5.30
30.00
30.00
4.00

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161015S0201 - Rev. A

11

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM35/16.PE.N screw clamp terminal blocks
Ground + neutral - 32 mm 1.260 in spacing
Description

35 mm²

N–– Simplify your PE.N connection with M35/16.P block connected to M35/16.N block through a pre-mounted
jumper,–– Adapted to TNS and TNC-S electrical network.

Ordering details

1SNC161169F0014

Description
Ground+ neutral

Color
Screw rail connection

TypePart Number

Green-yellow,
blue

M35/16.PE.N

IEC

UL

1SNA165575R2500

Main technical data

1 conductor
per clamp
M35/16.PE.N

CSA

Rigid: Solid/Stranded
6-50 mm²
Flexible without ferrule
6-35 mm²
Flexible with insulated ferrule
Gauge
B9

Rail
Wire stripping
lengthScrew clamp
Tool
Torque35 mm²4200 A

61.5
2.42"

Rail connection screw
Tool
Torque54
2.13"

59 2.32"
22 0.87"

Weight(1 pce) g

10

119.00

Mounting instructions

Rated cross section
Rated short-time withstand current (1s)

49 1.93"

Pkg
pce

G32, TH 35-7.5,
TH 35-15
17 mm
0.67 inFlat screwdriverØ 7 mmØ 0.32 in
2.8 - 3 N.m
24.6 - 26.1 lb.in
Flat screwdriverØ 5.5 mm
Ø 0.22 in
1 N.m
8.8 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

27 1.06"
CE

RoHS

Gost R

32 mm 1.260 in spacing

Accessories
Description
1

End stops

10 mm
5.2 mm

0.394 in
0.205 in

Dark grey

Type
BAM4
BAZ1

Part Number
1SNK900001R0000
1SNK900002R0000

Pkg

Weightpce(1 pce) g

50
50

14.00
5.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

11

1SNC161016S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

PAGE 241

1SNC161171S0201

12

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Disconnect
Overview					

244Screw clamp technology		
Disconnect with pull lever		
M4/6.D2.2S2

2 disconnect circuits

245

M4/6.D2.2S2.T

2 disconnect circuits and test

246

M4/6.D2.S1R

Change over type247

M4/6.D2.S1R.T

Change over type and test248

12
1SNC161171S0201

4 mm² / 10 AWG

PAGE 243

Dedicated applications terminal blocks
Disconnect

Screw clamp technology

Disconnect with pull lever
SectionIEC

UL/CSA

4 mm²

10 AWG

M4/6.D2.2S2

M4/6.D2.2S2.T

M4/6.D2.S1R

M4/6.D2.S1R.T

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

1SNC161170S0201 - Rev. A

12

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.D2.2S2 screw clamp terminal blocks
Disconnect with pull lever - with 2 independent circuits - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Save space with double deck terminal blocks: 2 idependent disconnect circuits in just 6 mm 0.236 in spacing,–– Black pull lever controls upper deck contact and grey pull lever controls lower deck contact,–– Closed terminal block: no end section needed.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161073F0014

Disconnect

M4/6.D2.2S2

111 4.37"

106 4.17"

103.5 4.07"

119 4.68"

114 4.48"

94.5 3.72"

111.5 4.38"

Grey, blackM4/6.D2.2S2

IEC

UL

1SNA199444R2500

Main technical data

1 conductor
per clamp

45.5 1.79"

With 2 independentcircuits

25

Weight(1 pce) g
30.00

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

12 A / 1 mm²
120 A
500 V
6000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CSA

Rail

G32, TH 35-7.5,
TH 35-15

24-10 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

10 A / 10 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
C

CE

RoHS

US

cCSAusGost R

Notes

50.5 1.98"

Mounting of the vertical jumper bar between
decks (ITVE2).

6 mm 0.236 in spacing

Interconnection between decks is possible oneach side of the switch, using accessory ITVE2.
Trap door opens with a screwdriver.

Accessories
Description
1

3

5

2

Type

Part Number

Pkg
pce

1
2
3

4

6

Color

4
5
6
7

End stops
10 mm
0.394 inJumper bars
1 poles
24 A
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Shield connectors
Inner deck jumper bars
Terminal block markers Blank card

Dark grey
Grey
Grey

White

BAZH1
AD2.5
PC6-2
PC6-3
PC6-4
PC6-10
EIP
CBD2S
ITVE2
RC610

1SNK900102R0000
1SNA114205R2000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA178408R1400
1SNA179825R2600
1SNA233000R0100

20
50
10
10
10
10
10
50
20
1

Weight(1 pce) g
24.00
1.60
2.00
2.00
3.00
8.00
1.30
7.50

1SNC161159S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

Technical data valid for copper conductors only.

PAGE 245

12

M4/6.D2.2S2 screw clamp terminal blocks
Disconnect with pull lever with 2 independent circuits and 4 test sockets - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Save space with double deck terminal blocks: 2 idependent disconnect circuits in just 6 mm 0.236 in spacing,–– Black pull lever controls upper deck contact and grey pull lever controls lower deck contact,–– Ease your test operations with the 2 built-in test sockets,–– Closed terminal block: no end section needed.

Ordering details
Description

Color

Type

Part Number

1SNC161073F0014

pce

Disconnect

With 2 independentcircuits and 4 test sockets
DIA 2 mm 0.079 inGrey, blackM4/6.D2.2S2.T

IEC

UL

1SNA199448R0100

Main technical data

1 conductor
per clamp

M4/6.D2.2S2

111 4.37"

106 4.17"

103.5 4.07"

119 4.68"

114 4.48"

25

Weight(1 pce) g
30.00

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

Rail

G32, TH 35-7.5,
TH 35-15

24-10 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

94.5 3.72"

111.5 4.38"

Pkg

12 A / 1 mm²
120 A
500 V
6000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

10 A / 10 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CCE

45.5 1.79"

RoHS

US

cCSAusGost R

50.5 1.98"

Notes
6 mm 0.236 in spacing

Mounting of the vertical jumper bar between
decks (ITVE2).
Interconnection between decks is possible oneach side of the switch, using accessory ITVE2.
Trap door opens with a screwdriver.

Accessories

3

5

12

2

Type

Part Number

1
2
3

4
5
6
7
8

End stops
10 mm
0.394 inJumper bars
1 poles
24 A
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Test plugs
DIA 2 mm 0.079 in
Shield connectors
Inner deck jumper bars
Terminal block markers Blank card

Dark grey
Grey
Grey

Black

White

BAZH1
AD2.5
PC6-2
PC6-3
PC6-4
PC6-10
EIP
FC2
CBD2S
ITVE2
RC610

1SNK900102R0000
1SNA114205R2000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA007865R2600
1SNA178408R1400
1SNA179825R2600
1SNA233000R0100

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

Pkg
pce

4

6

Color

8

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

20
50
10
10
10
10
10
100
50
20
1

Weight(1 pce) g
24.00
1.60
2.00
2.00
3.00
8.00

1.30
7.50
1SNC161160S0201 Rev. B

Description1

M4/6.D2.S1R screw clamp terminal blocks
Disconnect with pull lever - change over type - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Direct a signal either to the upper deck (contact control pull lever in high position), or to the lower deck (pulllever in low position) with just one operation,–– Closed terminal block: no end section needed.

Ordering details
Description
1SNC161337F0014

Disconnect

Color
Change over type

Type

Part Number

Grey, blackM4/6.D2.S1R

IEC

UL

1SNA199452R2500

Main technical data

1 conductor
per clamp

104.5 4.11"

102 4.01"

25

30.00

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

12 A / 1 mm²
120 A
500 V
6000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Rail

G32, TH 35-7.5,
TH 35-15

24-10 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

10 A / 10 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

99.5 3.91"

112.5 4.42"

110 4.33"

107.5 4.23"

Weight(1 pce) g

CSA

M4/6.D2.S1R

94.5 3.72"

Pkg
pce

C

CE

RoHS

US

cCSAusGost R

45.5 1.79"
50.5 1.99"

6 mm 0.236 in spacing

Accessories
Description

3

5

2

1
2
3

4

6

4
5
6

End stops
10 mm
0.394 inJumper bars
1 poles
24 A
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Shield connectors
Terminal block markers Blank card

Dark grey
Grey
Grey

White

Type
BAZH1
AD2.5
PC6-2
PC6-3
PC6-4
PC6-10
EIP
CBD2S
RC610

Part Number
1SNK900102R0000
1SNA114205R2000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA178408R1400
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
50
10
10
10
10
10
50
1

24.00
1.60
2.00
2.00
3.00
8.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
1SNC161161S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

PAGE 247

12

M4/6.D2.S1R screw clamp terminal blocks
Disconnect with pull lever - change over type with 3 test sockets 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Direct a signal either to the upper deck (contact control pull lever in high position), or to the lower deck (pulllever in low position) with just one operation,–– Ease your test operations with the built-in test sockets,–– Closed terminal block: no end section needed.

Ordering details
1SNC161337F0014

Description
Disconnect

Color
Change over typewith 3 test sockets
DIA 2 mm 0.079 in

TypePart Number

Grey, blackM4/6.D2.S1R.T

IEC

UL

1SNA199456R2100

Main technical data

1 conductor
per clamp

M4/6.D2.S1R

104.5 4.11"

102 4.01"

99.5 3.91"

112.5 4.42"

110 4.33"

Weight(1 pce) g

25

30.00

Mounting instructions

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.2-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

Rail

G32, TH 35-7.5,
TH 35-15

24-10 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

94.5 3.72"

107.5 4.23"

Pkg
pce

12 A / 1 mm²
120 A
500 V
6000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

10 A / 10 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CCE

45.5 1.79"

RoHS

US

cCSAusGost R

50.5 1.99"

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

1
2
3

4

6

4
5
6
7

End stops
10 mm
0.394 inJumper bars
1 poles
24 A
Lateral jumper bars 2 poles
35 A
3 poles
4 poles
10 polesInsulating tips
For lateral jumper bars type PC...
Test plugs
DIA 2 mm 0.079 in
Shield connectors
Terminal block markers Blank card

Color
Dark grey
Grey
Grey

Black
White

Type
BAZH1
AD2.5
PC6-2
PC6-3
PC6-4
PC6-10
EIP
FC2
CBD2S
RC610

Part Number
1SNK900102R0000
1SNA114205R2000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNA113550R2400
1SNA007865R2600
1SNA178408R1400
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
50
10
10
10
10
10
100
50
1

24.00
1.60
2.00
2.00
3.00
8.00

7.50

12

1SNC161162S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS12PAGE 249

1SNC160105S0201

13

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSDedicated applications terminal blocks
Component holder
Overview					

252Screw clamp technology		
Component holder		
4 mm² / 12 AWG

M4/6.DE1.D

With 2 diodes

253

M4/6.DE1.D1

With 2 diodes

254

M4/6.DE2.D

With 2 diodes

255

M4/6.DD

With 1 diode256

M4/6.DD1

With 1 diode257

M4/6.DE

Open circuit258

M4/6.DE1Open circuit259

M4/6.DE2Open circuit

260

For 5 x 20 mm and 5 x 25 mm fuses
4 mm² / 12 AWG

D4/8.D2.P.SF		

261

D4/8.D2.P.SFL		

262

D4/8.D2.P.SFD		

262

ADO-ADO technology
Component holder		D1.5/6.ADO.D1

With diode263

1SNC160105S0201

1.5 mm²

PAGE 251

13

Dedicated applications terminal blocks
Component holder
Screw clamp technology

Component holder
SectionIEC

UL/CSA4 mm²12 AWG

M4/6.DE1.D

M4/6.DE1.D1

M4/6.DE2.D

M4/6.DD

M4/6.DD1

M4/6.DE

M4/6.DE1

M4/6.DE2

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

6 mm 0.236 in

For 5 x 20 mm
and 5 x 25 mm fuses
SectionIEC

UL/CSA

D4/8.D2.P.SF
4 mm²

12 AWG

8 mm 0.315 in

D4/8.D2.P.SFL
8 mm 0.315 in

D4/8.D2.P.SFD
8 mm 0.315 in

ADO-ADO technology

Component
holderSectionIEC

1.5 mm²

UL/CSA

D1.5/6.ADO.D1

1SNC160062S0201

6 mm 0.236 in

13

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.DE screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
4 mm²

Description
Ease the test operation with two 1N4007 diodes.

Ordering details
Description

1SNC161219F0014

Component
holder

67 2.64"64.5 2.54"

Grey

Part Number

M4/6.DE1.D

1SNA115371R2600

UL

CSA

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg

Weightpce(1 pce) g

50

16.00

Mounting instructions
IEC

M4/6.DE

59.5 2.34"

With two 1N4007
diodes, common on
cathode (1000V peak250V Service-1A)

Type

Main technical data
1 conductor
per clamp

65.5 2.58"

Color

20 A / 4 mm²
480 A
500 V
IP20

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

33 1.30"
38 1.50"

6 mm 0.236 in spacing

Accessories
Description
2

3

4

5

6

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161144S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 25313

M4/6.DE screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
4 mm²

Description
Ease the test operation with two 1N4007 diodes.

Ordering details
Description

1SNC161219F0014

Component
holder

67 2.64"64.5 2.54"

Grey

Part Number

M4/6.DE1.D1

1SNA115591R0400

UL

CSA

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg

Weightpce(1 pce) g

50

16.00

Mounting instructions
IEC

M4/6.DE

59.5 2.34"

With two 1N4007
diodes, common on
anode (1000V peak250V Service-1A)

Type

Main technical data
1 conductor
per clamp

65.5 2.58"

Color

20 A / 4 mm²
480 A
500 V
IP20

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

33 1.30"
38 1.50"

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

1SNC161150S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

13

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.DE screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
4 mm²

Description
Ease the test operation with two 1N4007 diodes.

Ordering details
Description

1SNC161220F0014

Component
holder

67 2.64"64.5 2.54"

Grey

Part Number

M4/6.DE2.D

1SNA115327R1200

UL

CSA

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Pkg

Weightpce(1 pce) g

50

20.00

Mounting instructions
IEC

M4/6.DE

59.5 2.34"

With two 1N4007
diodes, common on
cathode (1000V peak250V Service-1A)

Type

Main technical data
1 conductor
per clamp

65.5 2.58"

Color

20 A / 4 mm²
480 A
500 V
IP20

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

Gost R

33 1.30"
38 1.50"

6 mm 0.236 in spacing

Accessories
Description
2

3

4

5

6

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161143S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 255

13

M4/6.DD screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description
Protect or test your circuit with one 1N4007 diodes.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161208F0014

Component
holder

67 2.64"

M4/6.DD

1SNA115168R2300

50

Mounting instructions
IEC

M4/6.DD

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

18-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

20 A / 4 mm²
480 A
500 V

25 A / 12 AWG 25 A / 12 AWG

IP20NEMA 1

600 V

150 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
59.5 2.34"

64.5 2.54"

Grey

Main technical data
1 conductor
per clamp

65.5 2.58"

Cathode of the blocking
diode connected to thelower circuit

Weight(1 pce) g
20.00

CE

RoHS

USR

CSA

Gost R

33 1.30"

Typical lamp test application

38 1.50"

6 mm 0.236 in spacing

PC61-10

Description
1

2

3

4

5

6

Color

Type

Part Number

Pkg
pce

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White

BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610

1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

13

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

20
20
10
10
10
10
10
10
10
1

Weight(1 pce) g
24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

1SNC161133S0201 - Rev. A

Accessories

M4/6.DD screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description
Protect or test your circuit with one 1N4007 diodes.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161208F0014

Component
holder

67 2.64"

M4/6.DD1

1SNA115184R0400

50

Mounting instructions
IEC

M4/6.DD

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

18-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

20 A / 4 mm²
480 A
500 V

25 A / 12 AWG 25 A / 12 AWG

IP20NEMA 1

600 V

150 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
59.5 2.34"

64.5 2.54"

Grey

Main technical data
1 conductor
per clamp

65.5 2.58"

Cathode of the blocking
diode connected to theupper circuit

Weight(1 pce) g
20.00

CE

RoHS

USR

CSA

Gost R

33 1.30"

Typical lamp test application

38 1.50"

6 mm 0.236 in spacing

PC61-10
Description
1

2

3

4

5

6

Color

Type

Part Number

Pkg
pce

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Dark grey
Grey

White

BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610

1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

20
20
10
10
10
10
10
10
10
1

Weight(1 pce) g
24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

PAGE 257

1SNC161135S0201 - Rev. A

Accessories

13

M4/6.DE screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
Description

4 mm²

Customize yourself the double deck terminal blocks by soldering electronic components (thickness 5 mm 0.200 in max).

12 AWG

Ordering details
Description

Color

1SNC161279F0014

Component holder Upper and lower circuit opened

Type
Grey

Part Number

M4/6.DE

1SNA115185R0500

Main technical data
Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

67 2.64"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20.00

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

22-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

26 A / 4 mm²
480 A
500 V

20 A / 12 AWG 20 A / 12 AWG

IP20NEMA 1

600 V

300 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

59.5 2.34"

64.5 2.54"

50

UL

M4/6.DE

65.5 2.58"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

CE

RoHS

USR

CSA

Gost R

33 1.30"
38 1.50"

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

1SNC161136S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

13

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSM4/6.DE screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
4 mm²
12 AWG

Description
Customize yourself the double deck terminal blocks by soldering electronic components (thickness 5 mm
0.200 in max).

Ordering details
Description

Color

1SNC161145F0014

Component holder Lower circuit opened

Type
Grey

Part Number

M4/6.DE1

1SNA115177R1400

Main technical data
Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

67 2.64"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20.00

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

22-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

26 A / 4 mm²
480 A
500 V

20 A / 12 AWG 20 A / 12 AWG

IP20NEMA 1

600 V

300 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

59.5 2.34"

64.5 2.54"

50

UL

M4/6.DE

65.5 2.58"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

RoHS

USR

CSA

Gost R

33 1.30"
38 1.50"

6 mm 0.236 in spacing

Accessories
Description
2

3

4

5

6

1
2
3

End stops
End sections
Jumper bars

10 mm
1 mm
6 mm

0.394 in
0.039 in
32 A

4
5
6

Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card

Dark grey
Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161134S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 259

13

M4/6.DE screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing
Description

4 mm²
12 AWG

Customize yourself the double deck terminal blocks by soldering electronic components (thickness 5 mm
0.200 in max).

Ordering details
Description

Color

1SNC161157F0014

Component holder Upper circuit opened

Type
Grey

Part Number

M4/6.DE2

1SNA115326R1100

Main technical data
UL

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

67 2.64"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20.00

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

26 A / 4 mm²
480 A
500 V

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

IP20

20 A / 12 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

59.5 2.34"

64.5 2.54"

50

CSA

M4/6.DE

65.5 2.58"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

RoHS

CSA

Gost R

33 1.30"
38 1.50"

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233000R0100

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
10
10
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
7.50

1SNC161142S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

13

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSD4/8.D2.P.SF screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - 8 mm 0.315 in spacing
Description

4 mm²–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not supplied with terminal blocks),–– Save space with double deck terminal blocks: 2 independent circuits 1 fuse on upper deck + 1 feed-through+ 1 ground.

12 AWG

Ordering details
Description

Color

1SNC161034F0014

Fuse

Type
Grey

Part Number

D4/8.D2.P.SF

1SNA400270R2000

Main technical data

Weight(1 pce) g

25

35.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

IEC

Rigid: Solid/Stranded
0.5-6 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

UL

CSA

Rail

TH 35-7.5,
TH 35-15

20-12 AWG

20-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

D4/8.D2.P.SF

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

6.3 A / 4 mm²

6.3 A / 12 AWG 6.3 A / 12 AWG

300 V
6000 V
IP20

300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

8 mm 0.315 in spacing

Accessories
1

3

2

4

5

6

7

8

9

10

1
2
3

10 mm
0.394 in
1.5 mm
0.059 in
2 poles
41 A
3 poles
4 poles
10 poles
4 Lateral jumper bars 10 poles
35 A
5 Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
6 Test sockets
DIA 2 mm 0.079 in
DIA 4 mm 0.157 in
7 Fuses
0.5 A
1A
2A
8 Assembly rods
2 poles
3 poles
4 poles
9 Neutral cartridges
10 Spring retaining rings
11 Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Grey

Type
BAZH1
FEM8D2S1
BJM8

PC81-10EL6
AL2
AL4-M3
FU520
TGA8

White

CN5
ANT
RC810

Part Number
1SNK900102R0000
1SNA400273R1700
1SNA168520R0500
1SNA168521R2200
1SNA168522R2300
1SNA168974R0000
1SNA173523R1100
1SNA173627R2100
1SNA163043R2100
1SNA206721R0100
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA179371R1600
1SNA168675R1400
1SNA234000R0200

Pkg

Weightqty(1 pce) g

20
20
10
10
10
10
10
10
50
50
10
10
10
10
10
10
10
10
1

24.00
4.60
5.00
7.00
9.50
23.70
5.00
0.10
0.90
1.10

1.00
3.90
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

11Technical data valid for copper conductors only.

PAGE 261

1SNC161078S0201 - Rev. B

Description

13

D4/8.D2.P.SF screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator - 8 mm 0.315 in spacing
Description

4 mm²–– Protect your circuits with 5 x 20 and 5 x 25 fuse terminal blocks (fuse not supplied with terminal blocks),–– Save space with double deck terminal blocks: 2 independent circuits 1 fuse on upper deck + 1 feed-through+ 1 ground,–– Quickly identify the defective circuit thanks to the blown fuse indicator.

12 AWG

Ordering details
1SNC161034F0014

Description
Fuse

Color

Type

Part Number

Grey

D4/8.D2.P.SFL

1SNA400271R1500

25

35.00

With blown fuse indicatorby LED 24-60 V DC /110 V ACGrey

D4/8.D2.P.SFD

1SNA400272R1600

25

35.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

Weight(1 pce) g

With blown fuse indicatorby neon 110-230 V AC

Main technical data
D4/8.D2.P.SF

Pkg
qty

IEC

Rigid: Solid/Stranded
0.5-6 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

TH 35-7.5,
TH 35-15

20-12 AWG

20-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

6.3 A / 4 mm²

6.3 A / 12 AWG 6.3 A / 12 AWG

300 V
6000 V
IP20

300 V

300 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR

CSA

Gost R

8 mm 0.315 in spacing

Notes
Blocks with LED indicator are labeled "+" on the outside of the lever. The indicator can be reversed in the field if
required.
Leakage current D4/8.D2.P.SFL: 110 V: < 0.5 mA / 230 V: < 0.7 mA
Leakage current D4/8.D2.P.SFD: 24 V: < 0.5 mA / 110 V: < 2.2 mA

Accessories
1

3

2

4

5

6

7

8

9

10

1
2
3

12 mm
0.472 in
1.5 mm
0.059 in
2 poles
41 A
3 poles
4 poles
10 poles
4 Lateral jumper bars 10 poles
35 A
5 Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
6 Test sockets
DIA 2 mm 0.079 in
DIA 4 mm 0.157 in
7 Fuses
0.5 A
1A
2A
8 Assembly rods
2 poles
3 poles
4 poles
9 Neutral cartridges
10 Spring retaining rings
11 Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Grey
Grey

Type
BAZH1
FEM8D2S1
BJM8

PC81-10EL6
AL2
AL4-M3
FU520
TGA8

White

CN5
ANT
RC810

Part Number
1SNK900102R0000
1SNA400273R1700
1SNA168520R0500
1SNA168521R2200
1SNA168522R2300
1SNA168974R0000
1SNA173523R1100
1SNA173627R2100
1SNA163043R2100
1SNA206721R0100
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA179371R1600
1SNA168675R1400
1SNA234000R0200

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

13

11Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
50
50
10
10
10
10
10
10
10
10
1

24.00
4.60
5.00
7.00
9.50
23.70
5.00
0.10
0.90
1.10

1.00
3.90
8.20

1SNC161081S0201 - Rev. B

Description

D1.5/6.ADO.D IDC terminal blocks
Component holder ADO-ADO - 6 mm 0.236 in spacing
1.5 mm²

Description–– Terminal blocks with built-in 1N5408 diode,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for control applications exposed to severe constrains (vibrations, shocks, corrosion etc.),–– Up to 2 wires per connection.

Ordering details
1SNC163069F0014

Description

Color

Type

Part Number

Pkg
pce

Component
holderWith diode (cathode on
the right)

Grey

D1.5/6.ADO.D1

1SNA199248R1000

Main technical data

Mounting instructions
IEC

ADO

50

Weight(1 pce) g
7.00

Rigid: Solid/Stranded
Flexible without ferrule

UL

CSA

0.34-1.5 mm²
0.34-1.5 mm²Rail

TH 35-7.5,
TH 35-15

Wire stripping
lengthD1.5/6.ADO.D

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Tool

Screw clamp

56 2.20"48.5 1.91"

45.5 1.79"

1 A / 1.5 mm²
180 A
80 V
IP20

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

Gost R

24 0.95"

6 mm 0.236 in spacing

Accessories
Description

3

5

2

1

End stops2
3

End sections
Jumper bars

4
5

Shield connectors
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

4

6

6

10 mm
5.2 mm3 mm
2 poles
3 poles
10 poles

0.394 in
0.205 in
0.118 in17.5 A

Dark grey
Grey
Orange

White

Type
BAM4
BAZ1
FEMAD3BJADO6-2
BJADO6-3
BJADO6-10
CBM5
OUPAD
OUMAD
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA199341R0500
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA178745R1400
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightpce(1 pce) g

50
50
20
20
20
10
50
1
1
1

14.00
5.30
2.50
1.00
1.00
6.00
205.00
29.00
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC163062S0201 - Rev. A

1

Color

Technical data valid for copper conductors only.

PAGE 263

13

14
INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

IndexPart number classification
Order code

Type

Page

Order code

Type

Page

Order code

Type

Page

1SNA007865R2600
1SNA008288R1500
1SNA008289R1600
1SNA008290R1300
1SNA008291R0000
1SNA008292R0100
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094310R2400
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA094360R0600
1SNA103189R2600
1SNA103588R2600
1SNA103619R0400
1SNA103620R0100
1SNA103672R0100
1SNA105028R2100
1SNA105141R2700
1SNA105142R2000
1SNA105265R0300
1SNA107239R0300
1SNA110106R2500
1SNA110251R0500
1SNA110264R0200
1SNA110269R1700
1SNA110327R2100
1SNA110328R0200
1SNA110331R2500
1SNA110332R2600
1SNA110333R2700
1SNA110368R1200
1SNA110415R1200
1SNA110418R2500
1SNA110439R2200
1SNA110440R0700
1SNA110441R2400
1SNA110442R2500
1SNA110491R1700
1SNA112086R0200
1SNA112098R1600
1SNA113067R1700
1SNA113137R0200
1SNA113542R1000
1SNA113544R1200
1SNA113546R1400
1SNA113548R2600
1SNA113550R2400
1SNA113629R2700
1SNA113689R2400
1SNA113690R2100
1SNA113691R1600
1SNA113692R1700
1SNA113762R2400
1SNA113885R0100
1SNA114117R0700
1SNA114195R0600
1SNA114205R2000
1SNA114328R2200
1SNA114329R2300
1SNA114434R0500
1SNA114522R0500
1SNA114778R0500
1SNA114825R0500
1SNA114836R0000
1SNA115139R1600
1SNA115140R2300

FC2
FU520
FU520
FU520
FU520
FU520
CPFT2
CPFT3
CPFT4
CPFT10CPFTR-2
CPFTR-3
CPFTR-4
CPFTR-10SCD
SCFT1SCFEX1SCFEX3SCF9DCB
M8.STP
M8.STP
MS6
FC2.MC
DR1.4
DR6
D6.LNTP1
D6.LNTP3
D6.LNTP2
D6.LNTP4
D6.LNTP6
D6.LNTP7
D6.LNTP8DR8.SF
D6.A.NTLP
D6.A.LLP
D6.NTLP
D6.NLP
D6.LLP
D6.LL
DR6.1
DR1.5.1
DR2.5.S1
FEM9
FEMT1
PC5-2
PC5-10
PC6-2
PC6-10
EIP
FEMT2
ECP26
ECP31
ECP35
ECP42
PEP
FEMS6
SCFD
FEMS8
AD2.5
FEMT3
BNT2
FEMR10
SCFT2
FEMT4
SCFM6
BAMH
M26.AF
M26.FF

19
34
34
34
34
34
176
176
176
176
176
176
176
176
214
167
239
112
101
182
168
168
112
53
114
117
217
218
219
221
223
222
220
121
224
225
213
214
215
216
118
116
120
101
167
17
17
18
18
17
157
84
85
86
87
84
112
213
113
66
165
165
65
157
162
66
84
88
84

1SNA115141R1000
1SNA115142R1100
1SNA115143R1200
1SNA115144R1300
1SNA115145R1400
1SNA115146R1500
1SNA115147R1600
1SNA115148R2700
1SNA115149R2000
1SNA115150R2500
1SNA115168R2300
1SNA115177R1400
1SNA115184R0400
1SNA115185R0500
1SNA115201R2500
1SNA115206R2200
1SNA115229R2000
1SNA115236R1700
1SNA115237R1000
1SNA115239R2200
1SNA115243R2600
1SNA115262R2100
1SNA115263R2200
1SNA115265R2400
1SNA115277R2000
1SNA115278R0100
1SNA115313R1400
1SNA115314R1500
1SNA115320R2700
1SNA115326R1100
1SNA115327R1200
1SNA115359R0200
1SNA115371R2600
1SNA115500R2500
1SNA115510R1600
1SNA115511R0300
1SNA115529R1500
1SNA115537R0500
1SNA115539R1700
1SNA115541R1100
1SNA115542R1200
1SNA115547R1700
1SNA115591R0400
1SNA115626R1600
1SNA115627R1700
1SNA115643R2700
1SNA115678R0200
1SNA115685R1200
1SNA115831R0400
1SNA115914R0700
1SNA115928R1500
1SNA115929R1600
1SNA115930R1300
1SNA115971R1000
1SNA116536R0500
1SNA116537R0600
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA116713R1600
1SNA116771R2000
1SNA116781R1300
1SNA116783R1500
1SNA116795R1100
1SNA116951R1500
1SNA116964R1200
1SNA116965R1300
1SNA116977R1700
1SNA116979R2100

M26.F
M31.AF
M31.FF
M31.F
M35.AF
M35.FF
M35.F
M42.AF
M42.FF
M42.F
M6.DD
M6.DE1
M6.DD1
M6.DE
M9.EE
MTC6
M6.SNTS
M8.ST
M8.ST1
M8.ST3
M8.ST7
M12.FF
M12.FF
MS6
M8.STP
MS8
M6.ST.Sn
M6.ST.Au
M10.RS
M6.DE2M6.DE2.D
M8.STA
M6.DE1.D
M8.STP3
DR1.5
M12.FF
M8.STP1
D2.6.DL
M10.ST-Sn
D2.6.DA
D2.6.D
D2.6.DAL2
M6.DE1.D1
M13.FF
M13.FF.1
D2.6.DPA1
M8.STP.RS
M8.RS
D8.ST1.RS.IP20
D8.ST.RS
D10.SNBTB1
D10.SNBTB2
M6.RS
M8.ST1.IP20
PC6-3
PC6-4
PC8-2
PC8-3
PC8-4
FEM12F
FED3E
FEMT5CVABM1SCFCV1-2
FEM8S
FED6
FEDA6
FEM13FFEMSTA

92
89
85
93
90
86
94
91
87
95
256
259
257
258
101
197
66
157
158
160
157
102
102
112
168
113
165
165
65
260
255
162
253
167
115
102
167
195
166
193
194
196
254
103
104
192
67
64
69
68
163
164
63
159
112
112
20
113
113
102
192
166
166
112
121
213
224
103
162

1SNA116987R0200
1SNA116991R0600
1SNA117318R2300
1SNA117600R0300
1SNA117668R0200
1SNA118368R1600
1SNA118499R2300
1SNA118707R0300
1SNA120251R0700
1SNA120491R1100
1SNA125117R0200
1SNA125119R1400
1SNA125121R0600
1SNA125358R0300
1SNA125487R0600
1SNA125593R0000
1SNA125711R1500
1SNA125930R1500
1SNA125961R1000
1SNA128035R1600
1SNA128361R0100
1SNA146227R2500
1SNA160496R2600
1SNA163043R2100
1SNA163155R2600
1SNA163181R1100
1SNA163311R2200
1SNA163313R2400
1SNA163315R2600
1SNA163394R2600
1SNA163403R2000
1SNA163409R0600
1SNA163418R2600
1SNA163424R1400
1SNA163860R0500
1SNA164406R2400
1SNA164581R1300
1SNA164582R1400
1SNA164583R1500
1SNA164585R1700
1SNA164586R1000
1SNA164587R1100
1SNA164588R2200
1SNA165575R2500
1SNA165680R0300
1SNA165683R2200
1SNA167224R2700
1SNA167319R0600
1SNA167674R0200
1SNA167860R0100
1SNA167908R0600
1SNA167927R1000
1SNA168201R1200
1SNA168202R1300
1SNA168203R1400
1SNA168204R1500
1SNA168205R1600
1SNA168206R1700
1SNA168207R1000
1SNA168208R2100
1SNA168273R1100
1SNA168401R0300
1SNA168520R0500
1SNA168521R2200
1SNA168522R2300
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400

FEMR8
FEMR8T
FEDR5
FEDR61
FEDR51
FEM6
FEM6D
SCF6
DR6.N
DR6.1.N
M6.NT
M8.NT
M10.NT
M16.NTMA2.5.NT
M12.NT1
MA2.5-2CPE
M6.N.RS
MA2.5.D2-2CPE
VRB3
VRB6
MTC6.Ex
DR6.P
AL2
REH3
PT101
PC61-10
PC8-10PC10-10VSJ11CPP263
CPP313
CPP353
CPP423
SFB1
BO3
BJS8
BJS8
BJS8
BJS10
BJS10
BJS10
BJS10
M16.PE.N
M12.PE.N
M10.PE.N
BJS13-10
AL2
CBD5
FC4
PC51-10
FC4-1
CPP262
CPP261
CPP312
CPP311
CPP352
CPP351
CPP422
CPP421
BJS10
EV8S
BJM8
BJM8
BJM8
TGA8
TGA8
TGA8
ANT

63
67
115
117
120
66
253
66
117
118
227
228
229
231
226
230
178
63
180
226
230
197
117
63
105
65
31
20
166
65
84
85
86
87
213
213
68
68
68
65
65
65
65
241
240
239
103
213
120
19
115
68
84
84
85
85
86
86
87
87
65
157
261
261
261
34
34
34
34
PAGE 26514

IndexPart number classification

14

Order code

Type

Page

Order code

Type

Page

Order code

Type

Page

1SNA168956R0600
1SNA168974R0000
1SNA173016R1000
1SNA173058R0200
1SNA173059R0300
1SNA173060R0000
1SNA173181R1300
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA173523R1100
1SNA173627R2100
1SNA173660R1600
1SNA173815R1600
1SNA173816R1700
1SNA173817R1000
1SNA173819R2200
1SNA173888R2000
1SNA173906R2200
1SNA173907R2300
1SNA173908R0400
1SNA174393R2000
1SNA174394R2100
1SNA174395R2200
1SNA174396R2300
1SNA174558R0500
1SNA174601R0100
1SNA174781R2500
1SNA174789R0500
1SNA175263T0600
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA176675R0400
1SNA176676R0500
1SNA176677R0600
1SNA176678R1700
1SNA176679R1000
1SNA176704R0200
1SNA176705R0300
1SNA176706R0400
1SNA176708R1600
1SNA176816R1200
1SNA177652R0600
1SNA177654R0000
1SNA177812R1700
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA178408R1400
1SNA178745R1400
1SNA178944R0400

SFB2
BJM8
SCDR61
DCV
DCJ
DCO
PSC
BJM62
BJM62
BJM62
BJM62
BJM62
PC81-10EL6COCF 32
BJS9.5-2
BJS9.5-3
BJS9.5-4
BJS9.5-10
BP8.A4
BRC-1
BRC-1.5
BRC-2.5
BJS12.5-2
BJS12.5-3
BJS12.5-5
BJS12.5-10
BRC-0.5
BRC-4
BJDP4
BJS8-20
ECR-3
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
BJMI10-2
BJMI10-3
BJMI10-4
BJMI10-5
BJMI10-10
BJMI5DR
BJMI5DR
BJMI5DR
BJMI5DR
CPV1-2
BJS5-20
BJS10-20
EL61
BJD6
BJD6
BJD6
BJD6
BJD6
BJD6
CBD2S
CBM5
OUPAD

213
261
114
226
112
113
165
117
117
117
213
117
33
20
176
101
101
101
101
64
165
165
165
102
102
102
102
165
165
63
68
102
17
17
17
17
17
18
18
18
18
18
20
20
20
20
20
166
166
166
166
166
115
115
115
115
112
116
65
192
192
192
192
192
192
192
27
17
17

1SNA179371R1600
1SNA179466R0600
1SNA179623R0300
1SNA179625R0500
1SNA179635R0700
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA179694R0300
1SNA179726R0200
1SNA179825R2600
1SNA183436R0500
1SNA190001R2000
1SNA190002R2100
1SNA190003R2200
1SNA190004R2300
1SNA190005R2400
1SNA190006R2500
1SNA190007R2600
1SNA190008R0700
1SNA190009R0000
1SNA190016R1600
1SNA190017R1700
1SNA190018R2000
1SNA190019R2100
1SNA196789R2400
1SNA196792R1700
1SNA196896R0000
1SNA199034R1500
1SNA199035R1600
1SNA199036R1700
1SNA199042R2500
1SNA199043R2600
1SNA199044R2700
1SNA199048R0300
1SNA199050R0100
1SNA199051R2600
1SNA199052R2700
1SNA199053R2000
1SNA199059R0600
1SNA199060R0300
1SNA199061R2000
1SNA199064R2300
1SNA199091R1700
1SNA199098R2600
1SNA199107R2400
1SNA199108R0500
1SNA199118R2600
1SNA199135R1700
1SNA199136R1000
1SNA199137R1100
1SNA199144R2000
1SNA199155R2300
1SNA199157R2500
1SNA199184R1100
1SNA199186R1300
1SNA199187R1400
1SNA199188R2500
1SNA199208R1100
1SNA199211R2300
1SNA199212R2400
1SNA199231R2700
1SNA199235R2300
1SNA199242R0200
1SNA199244R0400
1SNA199248R1000
1SNA199275R0300

CN5
OUMAD
BJDP1
BJDP3
CDB2
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
ITVE
AJS9
ITVE2
CVABM
D27.FF
D32.FF
D42.FF
D55.FF
D55.FF
D27.AF
D32.AF
D42.AF
D55.AF
CPUF35
CPUF70
CPUF120
CPUF185
BNSTP2
BNSTP1SCAD
D6.ADO
D6.ADO
D6.N.ADO
D8.ADO
D8.ADO
D8.N.ADO
D6.ADO.4
D6.P.ADO
D1.6.ADO
D1.6.ADO
D1.6.N.ADO
D2.8.ADO
D2.8.ADO
D2.8.N.ADO
D6.ADO.2
D2.8.P.ADO
D1.6.P.ADO
D6.SN.ADO
D6.SN.ADO
D8.P.ADO
BNT1
BNT3
D8.SN.ADO
D1.6.SNT2.ADO
D8.ADO.2
D8.ADO.4
D2.8.SFT.ADO2
D2.8.SNNT.ADO2
D2.8.SFLT.ADO2
D2.8.SFDT.ADO2
D1.8.SFT.ADO
D1.8.SFLT.ADO
D1.8.SFDT.ADO
D2.8.SNT2.ADO
D6.SNT2.ADO
D6.D2.ADO
D6.D2.N.ADO
D1.6.ADO.D1
DR6.ADO

121
17
20
20
50
253
253
253
253
253
49
68
245
165
74
75
76
77
78
79
80
81
82
74
75
76
77
67
67
18
18
18
18
20
20
20
19
18
42
42
42
43
43
43
19
43
42
31
31
20
165
165
33
51
21
21
55
55
56
56
53
54
54
52
32
27
27
263
134

1SNA199279R1700
1SNA199283R2400
1SNA199287R2000
1SNA199321R2100
1SNA199336R2000
1SNA199341R0500
1SNA199352R0000
1SNA199354R0200
1SNA199382R2700
1SNA199417R1200
1SNA199420R2100
1SNA199421R1600
1SNA199423R1000
1SNA199433R1200
1SNA199435R1400
1SNA199437R1600
1SNA199439R2000
1SNA199444R2500
1SNA199448R0100
1SNA199452R2500
1SNA199456R2100
1SNA199476R2500
1SNA199480R2600
1SNA199527R1000
1SNA199528R2100
1SNA199551R2000
1SNA199554R2300
1SNA199555R2400
1SNA199556R2500
1SNA199563R2400
1SNA199564R2500
1SNA199565R2600
1SNA205735R0600
1SNA205736R0700
1SNA205737R0000
1SNA205738R1100
1SNA205767R1600
1SNA205768R2700
1SNA205769R2000
1SNA205770R2500
1SNA205771R1200
1SNA205772R1300
1SNA205773R1400
1SNA205774R1500
1SNA205775R1600
1SNA205776R1700
1SNA205777R1000
1SNA205778R2100
1SNA205779R2200
1SNA205955R0300
1SNA205956R0400
1SNA205958R1600
1SNA205963R0300
1SNA205974R0600
1SNA205975R0700
1SNA205982R2700
1SNA206394R0200
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206721R0100
1SNA206722R0200
1SNA206723R0300
1SNA215266R0100
1SNA215580R2100
1SNA215999R2100
1SNA216110R2200

DR8.ADODR1.6.ADO
DR2.8.ADO
COCE
FEDAD1
FEMAD3
FEDAD4
FEDAD5
FEDAD7
FED2AD1
BADRL
FEAD1
FEAD2
FEAD5
FEAD6
FEAD3
FEAD4
M6.D2.2S2
M6.D2.2S2.T
M6.D2.S1R
M6.D2.S1R.T
FED2AD2
D1.6.D2.ADO
DS8.P.ADO
DS2.8.P.ADO
SCAD5
D2.5.ADO
D2.5.ADO
D2.5.N.ADO
D5.ADO
D5.ADO
D5.N.ADO
BJM4
BJM4
BJM4
BJM4
DRF6
DRF8
DRF10
DRF12
DRF16
BJS27-2
BJS27-3
BJS32-2
BJS32-3
BJS42-2
BJS42-3
BJS551-2
BJS551-3
BJADO5-2
BJADO5-3
BJADO5-5
BJADO5-10
BJADO6-2
BJADO6-3
BJADO6-10
EV6I
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5
AL4-M3
AL4-M3-R1
AL4-M4
FEM8T6
FED2-4
FED10S1
165LTTM5TM5

135
145
146
183
17
41
29
50
53
27
114
129
141
129
141
137
148
245
246
247
248
49
49
131
142
17
17
17
17
41
41
41
114
114
114
114
74
75
76
77
78
74
74
75
75
76
76
77
77
29
29
29
29
31
31
31
68
68
68
68
68
68
68
64
65
68
114
163
105

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

IndexPart number classification
Order code

Type

Page

Order code

Type

Page

Order code

Type

Page

1SNA216112R1000
1SNA216114R1200
1SNA229000R1500
1SNA230000R1200
1SNA231000R0700
1SNA232000R0000
1SNA233000R0100
1SNA234000R0200
1SNA235463R2300
1SNA236500R0600
1SNA237000R0500
1SNA238000R1600
1SNA280092R2500
1SNA280093R2600
1SNA290201R1100
1SNA290203R1300
1SNA290211R0200
1SNA290213R0400
1SNA290219R1200
1SNA290221R0400
1SNA290223R0600
1SNA290231R0600
1SNA290233R0000
1SNA290241R1000
1SNA290243R1200
1SNA290261R1400
1SNA290281R0100
1SNA290322R0100
1SNA290324R0300
1SNA290326R0500
1SNA290328R1700
1SNA290330R1500
1SNA290350R2100
1SNA290352R1700
1SNA290354R1100
1SNA290356R1300
1SNA290358R2500
1SNA290360R2300
1SNA290365R1400
1SNA290366R1500
1SNA290367R1600
1SNA290451R0300
1SNA290452R0400
1SNA290453R0500
1SNA290454R0600
1SNA290455R0700
1SNA290483R2400
1SNA290484R2500
1SNA290486R2700
1SNA290487R2000
1SNA290501R0000
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA291110R2600
1SNA291301R0200
1SNA291311R2300
1SNA291322R2600
1SNA291323R2700
1SNA291324R2000
1SNA291325R2100
1SNA291559R0400
1SNA291560R0100
1SNA291833R1700
1SNA296114R1300
1SNA296117R1600
1SNA299489R0700
1SNA299493R2300

165ETTM5TM5
FEET80
RC410
RC55
RC510
RC65
RC610
RC810
RPA
RCT810
RCAL85
RC1010
CPE43
CPE80
DR2.5.2L
DR2.5.N.2L
DR2.10.4L
DR2.10.N.4L
DR2.10.P.4L
DS2.5.2L
DS2.5.N.2L
DS2.10.4L
DS2.10.N.4L
DB2.5.2L
DB2.5.N.2L
DH2.5.2L
FEDB.L
D2.5.NTLP.L
D2.5.NLP.L
D2.5.LLP.L
D2.5.LL.L
D2.5.NL.L
D2.5.C3.L
D2.5.C3.L.L
D2.5.C4.L
D2.5.C4.L.L
FED5.C3.L
FED5.C4.L
PC5.34PC5.34PC5.34
BJE762.2
BJE762.5
BJE762.10
EIP
RB-12W7
D2.7.ADO-CPE
D2.7.2ADO-CPE
D1.7.ADO-CPE
D1.7.2ADO-CPE
DS2.10.4L.YL
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDL5-10
FED1.L
FED2.LBJDL10-2
BJDL10-3
BJDL10-4
BJDL10-5
FED5.L.A
FED5.L.B
FECPE.2ADO
FEET80165ETTM5TM5-2
DS6.ADO
DS8.ADO

106
105
114
115
17
117
18
20
96
101
131
65
103
105
124
124
125
125
124
122
122
123
123
127
127
128
127
232
233
234
232
234
198
199
200
201
198
200
198
198
198
183
183
183
183
183
184
186
183
185
123
122
122
122
122
122
122
122
123
123
123
123
232
233
185
107
107
130
131

1SNA299497R2700
1SNA299501R0300
1SNA299505R0700
1SNA299509R1300
1SNA299513R2600
1SNA299517R2200
1SNA299521R2600
1SNA299529R0600
1SNA299552R0500
1SNA299554R0700
1SNA299555R0000
1SNA299556R0100
1SNA299557R0200
1SNA299558R1300
1SNA299559R1400
1SNA299632R0500
1SNA299633R0600
1SNA299777R1600
1SNA399030R0500
1SNA399031R2200
1SNA399226R0200
1SNA399228R1400
1SNA399231R0700
1SNA399244R1400
1SNA399245R1500
1SNA399250R2600
1SNA399251R1300
1SNA399318R1600
1SNA399319R1700
1SNA399491R2500
1SNA399495R2100
1SNA399509R1700
1SNA399513R2200
1SNA399514R2300
1SNA399518R0700
1SNA399519R0000
1SNA399600R2600
1SNA399678R2700
1SNA399679R2000
1SNA399683R0500
1SNA399684R0600
1SNA399685R0700
1SNA399689R1300
1SNA399690R1000
1SNA399692R0600
1SNA399693R0700
1SNA399707R1500
1SNA399708R2600
1SNA399709R2700
1SNA399758R2700
1SNA399762R1300
1SNA399766R1700
1SNA399768R2100
1SNA399770R2700
1SNA399777R1200
1SNA399779R2400
1SNA399782R0000
1SNA399785R0300
1SNA399800R1700
1SNA399801R0400
1SNA399856R0200
1SNA399886R2100
1SNA399931R2500
1SNA400063R0000
1SNA400270R2000
1SNA400271R1500
1SNA400272R1600
1SNA400273R1700
1SNA400711R0600

DS1.6.ADO
DS2.8.ADO
DB6.ADO
DB8.ADO
DB1.6.ADO
DB2.8.ADO
DH6.ADO
DH1.6.ADO
DRE6.ADO
DRE1.6.ADO
DRE2.8.ADO
DSE6.ADO
DSE8.ADO
DSE1.6.ADO
DSE2.8.ADO
DR8.P.ADO
DR2.8.P.ADO
COC 1
D2.5.P.ADO
D5.P.ADO
D2.5.SN.ADO
D2.5.SNT2.ADO
D5.SNT2.ADO
D8.ADO
D8.ADO3
D8.P.ADO
D8.P.ADO3
D8.N.ADO
D8.N.ADO3
DR5.ADO
DRE5.ADO
DR2.5.ADO
DRE2.5.ADO
DS2.5.ADO
DSE2.5.ADO
DB2.5.ADO
D8.D2.ADO
FED5.C3.ADO
FED5.C4.ADO
PC52.10
PC52.10
PC52.10
D5.C3.ADO
D5.C3.ADO.L
D5.C4.ADO
D5.C4.ADO.L
PC52.66
PC52.66
PC52.66
FEDAD10
D8.SFT2.I.ADO2
D8.SNNT2.I.ADO2
D8.SFLT2.I.ADO2
D8.SFDT2.I.ADO2
D8.SFT2.I.ADO
D8.SNNT2.I.ADO
D8.SFDT2.I.ADO
D8.SF.I.ADO
D8.ADO3
D8.ADO
D8.SFLT2.I.ADO
SPBO.NT.L
D6.D1.P.ADO
VRADO.CPE7
D8.D2.P.SF
D8.D2.P.SFL
D8.D2.P.SFD
FEM8D2S1
PC8-R1

141
142
138
139
148
149
140
150
134
145
146
130
131
141
142
135
146
176
17
41
29
30
50
44
22
44
22
44
22
144
144
133
133
129
129
137
28
202
204
202
202
202
202
203
204
205
202
202
202
34
37
37
38
38
35
34
36
34
22
44
36
232
27
183
261
262
262
261
157

1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400753R1000
1SNA400813R0000
1SNA400814R0000
1SNA400815R0000
1SNA400817R0000
1SNA400818R0000
1SNA400819R0000
1SNA400821R0000
1SNA400822R0000
1SNA400823R0000
1SNA400824R0000
1SNA400825R0000
1SNA400826R0000
1SNA400827R0000
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000

PC8-R2
PC8-R3
PC8-R4
M12.FFMA2.5.D2-2CPE
MA2.5-CPE
MA2.5-SNB-CPE
MA2.5-2CPE
ENS.FEDBCPENS.FE-BCP
MA2.5-2CPE1-Pb
MA2.5-CPE.1
MA2.5.D-2CPE
FEM6
FEDCP
FE2CPE
MA2.5-CPE
BAM4
BAZ1
BAZH1
SC-JB8-2
SC-JB8-3
SC-JB8-4

157
157
157
102
180
176
182
178
180
176
179
177
181
176
180
178
176
17
17
27
68
68
68

14
PAGE 267

IndexType classification
Type

Order code

Page

Type

Order code

Page

Type

Order code

Page

165ETTM5TM5165ETTM5TM5-2
165LTTM5TM5
AD2.5
AJS9
AJS9-1AJS9-2
AJS9-3
AJS9-4AJS9-5AL2

1SNA216112R1000
1SNA296117R1600
1SNA216110R2200
1SNA114205R2000
1SNA179726R0200
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA163043R2100
1SNA167319R0600
1SNA206721R0100
1SNA206722R0200
1SNA206723R0300
1SNA168675R1400
1SNA199420R2100
1SNK900001R0000
1SNA114836R0000
1SNK900002R0000
1SNK900102R0000
1SNA205963R0300
1SNA205955R0300
1SNA205956R0400
1SNA205958R1600
1SNA205982R2700
1SNA205974R0600
1SNA205975R0700
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA291322R2600
1SNA291323R2700
1SNA291324R2000
1SNA291325R2100
1SNA291110R2600
1SNA291102R2300
1SNA291103R2400
1SNA291104R2500
1SNA291105R2600
1SNA179623R0300
1SNA179625R0500
1SNA174781R2500
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA205735R0600
1SNA205736R0700
1SNA205737R0000
1SNA205738R1100
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA168520R0500
1SNA168521R2200
1SNA168522R2300
1SNA168974R0000
1SNA176679R1000
1SNA176675R0400
1SNA176676R0500
1SNA176677R0600
1SNA176678R1700
1SNA176282R2300
1SNA176278R1600

106
107
106
248
169
170
170
170
170
170
262
225
262
106
65
262
147
263
95
263
262
144
144
144
29
263
263
263
196
196
196
196
196
196
125
125
125
125
236
236
236
236
236
44
44
63
186
186
186
114
114
114
114
225
225
225
225
225
262
262
262
262
166
166
166
166
166
181
181

BJMI5-3
BJMI5-4
BJMI5-5
BJMI5DR

1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176704R0200
1SNA176705R0300
1SNA176706R0400
1SNA176708R1600
1SNA176667R0400
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA179672R1400
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA176673R0200
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA164585R1700
1SNA164586R1000
1SNA164587R1100
1SNA164588R2200
1SNA168273R1100
1SNA177654R0000
1SNA174396R2300
1SNA174393R2000
1SNA174394R2100
1SNA174395R2200
1SNA167224R2700
1SNA205772R1300
1SNA205773R1400
1SNA205774R1500
1SNA205775R1600
1SNA205776R1700
1SNA205777R1000
1SNA177652R0600
1SNA205778R2100
1SNA205779R2200
1SNA164581R1300
1SNA164582R1400
1SNA164583R1500
1SNA174789R0500
1SNA173819R2200
1SNA173815R1600
1SNA173816R1700
1SNA173817R1000
1SNA196792R1700
1SNA196789R2400
1SNA199135R1700
1SNA114329R2300
1SNA199136R1000
1SNA164406R2400
1SNA173888R2000
1SNA174558R0500
1SNA173906R2200
1SNA173907R2300
1SNA173908R0400
1SNA174601R0100
1SNA178408R1400
1SNA167674R0200
1SNA178745R1400
1SNA179635R0700
1SNA179371R1600
1SNA299777R1600
1SNA199321R2100

181
181
178
116
116
116
116
63
63
63
63
63
260
260
260
260
260
64
64
64
64
64
65
65
65
65
65
65
102
102
102
102
104
79
79
80
80
81
81
116
82
82
169
169
169
169
101
101
101
101
168
168
166
166
166
232
168
166
166
166
166
166
248
120
263
51
262
182
186

COCF 32
CPE43
CPE80
CPFT10
CPFT2
CPFT3
CPFT4
CPFTR-10
CPFTR-2
CPFTR-3
CPFTR-4
CPP261
CPP262
CPP263
CPP311
CPP312
CPP313
CPP351
CPP352
CPP353
CPP421
CPP422
CPP423
CPUF120
CPUF185
CPUF35
CPUF70CPV1-2CVABM
CVABM1D1.6.ADO

1SNA173660R1600
1SNA280092R2500
1SNA280093R2600
1SNA094310R2400
1SNA094302R2100
1SNA094303R2200
1SNA094304R2300
1SNA094360R0600
1SNA094352R2200
1SNA094353R2300
1SNA094354R2400
1SNA168202R1300
1SNA168201R1200
1SNA163403R2000
1SNA168204R1500
1SNA168203R1400
1SNA163409R0600
1SNA168206R1700
1SNA168205R1600
1SNA163418R2600
1SNA168208R2100
1SNA168207R1000
1SNA163424R1400
1SNA190018R2000
1SNA190019R2100
1SNA190016R1600
1SNA190017R1700
1SNA176816R1200
1SNA183436R0500
1SNA116783R1500
1SNA199051R2600
1SNA199052R2700
1SNA199248R1000
1SNA199480R2600
1SNA199053R2000
1SNA199098R2600
1SNA199144R2000
1SNA290487R2000
1SNA290486R2700
1SNA199212R2400
1SNA199211R2300
1SNA199208R1100
1SNA199563R2400
1SNA199564R2500
1SNA399689R1300
1SNA399690R1000
1SNA399692R0600
1SNA399693R0700
1SNA199565R2600
1SNA399031R2200
1SNA399231R0700
1SNA190008R0700
1SNA190003R2200
1SNA190009R0000
1SNA190004R2300
1SNA199554R2300
1SNA199555R2400
1SNA290350R2100
1SNA290352R1700
1SNA290354R1100
1SNA290356R1300
1SNA290328R1700
1SNA290326R0500
1SNA199556R2500
1SNA290330R1500
1SNA290324R0300
1SNA290322R0100
1SNA399030R0500
1SNA399226R0200

182
104
107
182
182
182
182
182
182
182
182
92
92
92
93
93
93
94
94
94
95
95
95
81
82
79
80
113
165
166
42
42
263
49
42
46
51
185
183
54
54
53
41
41
202
203
204
205
41
45
50
81
76
82
77
17
17
198
199
200
201
236
235
17
235
233
232
23
29

AL4-M3
AL4-M3-R1
AL4-M4
ANT
BADRL
BAM4
BAMH
BAZ1
BAZH1
BJADO5-10
BJADO5-2
BJADO5-3
BJADO5-5
BJADO6-10
BJADO6-2
BJADO6-3
BJD6

BJDL10-2
BJDL10-3
BJDL10-4
BJDL10-5
BJDL5-10
BJDL5-2
BJDL5-3
BJDL5-4
BJDL5-5
BJDP1
BJDP3
BJDP4
BJE762.10
BJE762.2
BJE762.5
BJM4

BJM62

BJM8

14

BJMI10-10
BJMI10-2
BJMI10-3
BJMI10-4
BJMI10-5
BJMI5-10
BJMI5-2

BJMI6-10
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6D-10
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI8-10
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJS10

BJS10-20
BJS12.5-10
BJS12.5-2
BJS12.5-3
BJS12.5-5
BJS13-10
BJS27-2
BJS27-3
BJS32-2
BJS32-3
BJS42-2
BJS42-3
BJS5-20
BJS551-2
BJS551-3
BJS8

BJS8-20
BJS9.5-10
BJS9.5-2
BJS9.5-3
BJS9.5-4
BNSTP1BNSTP2
BNT1
BNT2
BNT3
BO3
BP8.A4
BRC-0.5
BRC-1
BRC-1.5
BRC-2.5
BRC-4
CBD2S
CBD5
CBM5
CDB2
CN5
COC 1
COCE

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKS

D1.6.ADO.D1
D1.6.D2.ADO
D1.6.N.ADO
D1.6.P.ADO
D1.6.SNT2.ADO
D1.7.2ADO-CPE
D1.7.ADO-CPE
D1.8.SFDT.ADO
D1.8.SFLT.ADO
D1.8.SFT.ADO
D5.ADO
D5.C3.ADO
D5.C3.ADO.L
D5.C4.ADO
D5.C4.ADO.L
D5.N.ADO
D5.P.ADO
D5.SNT2.ADO
D42.AF
D42.FF
D55.AF
D55.FFD2.5.ADO
D2.5.C3.L
D2.5.C3.L.L
D2.5.C4.L
D2.5.C4.L.L
D2.5.LL.L
D2.5.LLP.L
D2.5.N.ADO
D2.5.NL.L
D2.5.NLP.L
D2.5.NTLP.L
D2.5.P.ADO
D2.5.SN.ADO

IndexType classification
Type

Order code

Page

Type

Order code

Page

Type

Order codePage

D2.5.SNT2.ADO
D2.6.D
D2.6.DA
D2.6.DAL2
D2.6.DL
D2.6.DPA1
D2.7.2ADO-CPE
D2.7.ADO-CPE
D2.8.ADO

1SNA399228R1400
1SNA115542R1200
1SNA115541R1100
1SNA115547R1700
1SNA115537R0500
1SNA115643R2700
1SNA290484R2500
1SNA290483R2400
1SNA199059R0600
1SNA199060R0300
1SNA199061R2000
1SNA199091R1700
1SNA199188R2500
1SNA199187R1400
1SNA199184R1100
1SNA199186R1300
1SNA199231R2700
1SNA190005R2400
1SNA190006R2500
1SNA190001R2000
1SNA110418R2500
1SNA110415R1200
1SNA199034R1500
1SNA199035R1600
1SNA199064R2300
1SNA199048R0300
1SNA399931R2500
1SNA199242R0200
1SNA199244R0400
1SNA110442R2500
1SNA110441R2400
1SNA110264R0200
1SNA110327R2100
1SNA110269R1700
1SNA110328R0200
1SNA110331R2500
1SNA110332R2600
1SNA110333R2700
1SNA199036R1700
1SNA110440R0700
1SNA110439R2200
1SNA199050R0100
1SNA199107R2400
1SNA199108R0500
1SNA199235R2300
1SNA399244R1400
1SNA399801R0400
1SNA400270R2000
1SNA400272R1600
1SNA400271R1500
1SNA399318R1600
1SNA399250R2600
1SNA399785R0300
1SNA399782R0000
1SNA399770R2700
1SNA399856R0200
1SNA399768R2100
1SNA399777R1200
1SNA399762R1300
1SNA199137R1100
1SNA399779R2400
1SNA399766R1700
1SNA115928R1500
1SNA115929R1600
1SNA199042R2500
1SNA199043R2600
1SNA199155R2300
1SNA199157R2500
1SNA399245R1500

30
194
193
196
195
192
186
184
43
43
43
47
56
56
57
57
52
78
79
74
225
224
18
18
19
19
27
27
27
216
215
217
219
218
221
223
222
220
18
214
213
24
31
31
32
44
44
261
262
262
44
48
34
36
38
36
38
39
40
33
39
40
163
164
20
20
21
21
22

D8.D2.ADO
D8.N.ADO
D8.N.ADO3
D8.P.ADO
D8.P.ADO3
D8.ST.RS
D8.ST1.RS.IP20
D32.AF
D32.FF
DB1.6.ADO
DB2.5.2L
DB2.5.ADO
DB2.5.N.2L
DB2.8.ADO
DB6.ADO
DB8.ADO
DCB
DCJ
DCO
DCV
DH1.6.ADO
DH2.5.2L
DH6.ADODR1.4
DR1.5
DR1.5.1
DR1.6.ADO
DR5.ADODR2.10.4L
DR2.10.N.4L
DR2.10.P.4L
DR2.5.2L
DR2.5.ADO
DR2.5.N.2L
DR2.5.S1
DR2.8.ADO
DR2.8.P.ADO
DR6
DR6.1
DR6.1.N
DR6.ADO
DR6.N
DR6.P
DR8.ADO
DR8.P.ADO
DR8.SF
DRE1.6.ADO
DRE5.ADO
DRE2.5.ADO
DRE2.8.ADO
DRE6.ADO
DRF10
DRF12
DRF16
DRF6
DRF8
DS1.6.ADO
DS2.10.4L
DS2.10.4L.YL
DS2.10.N.4L
DS2.5.2L
DS2.5.ADO
DS2.5.N.2L
DS2.8.ADO
DS2.8.P.ADO
DS6.ADO
DS8.ADO
DS8.P.ADO

1SNA399800R1700
1SNA399600R2600
1SNA199044R2700
1SNA399319R1700
1SNA199118R2600
1SNA399251R1300
1SNA115914R0700
1SNA115831R0400
1SNA190007R2600
1SNA190002R2100
1SNA299513R2600
1SNA290241R1000
1SNA399519R0000
1SNA290243R1200
1SNA299517R2200
1SNA299505R0700
1SNA299509R1300
1SNA105028R2100
1SNA173059R0300
1SNA173060R0000
1SNA173058R0200
1SNA299529R0600
1SNA290261R1400
1SNA299521R2600
1SNA110106R2500
1SNA115510R1600
1SNA112086R0200
1SNA199283R2400
1SNA399491R2500
1SNA290211R0200
1SNA290213R0400
1SNA290219R1200
1SNA290201R1100
1SNA399509R1700
1SNA290203R1300
1SNA112098R1600
1SNA199287R2000
1SNA299633R0600
1SNA110251R0500
1SNA110491R1700
1SNA120491R1100
1SNA199275R0300
1SNA120251R0700
1SNA160496R2600
1SNA199279R1700
1SNA299632R0500
1SNA110368R1200
1SNA299554R0700
1SNA399495R2100
1SNA399513R2200
1SNA299555R0000
1SNA299552R0500
1SNA205769R2000
1SNA205770R2500
1SNA205771R1200
1SNA205767R1600
1SNA205768R2700
1SNA299497R2700
1SNA290231R0600
1SNA290501R0000
1SNA290233R0000
1SNA290221R0400
1SNA399514R2300
1SNA290223R0600
1SNA299501R0300
1SNA199528R2100
1SNA299489R0700
1SNA299493R2300
1SNA199527R1000

22
28
20
22
25
26
169
170
80
75
148
127
137
127
149
138
139
182
112
113
227
150
128
140
114
115
116
145
144
125
125
126
124
133
124
120
146
147
117
118
118
134
117
119
135
136
121
145
144
133
146
134
81
82
78
79
80
141
123
123
123
122
129
122
142
143
130
131
132

DSE1.6.ADO
DSE2.5.ADO
DSE2.8.ADO
DSE6.ADO
DSE8.ADO
ECP26
ECP31
ECP35
ECP42
ECR-3
EIP

1SNA299558R1300
1SNA399518R0700
1SNA299559R1400
1SNA299556R0100
1SNA299557R0200
1SNA113689R2400
1SNA113690R2100
1SNA113691R1600
1SNA113692R1700
1SNA175263T0600
1SNA113550R2400
1SNA290454R0600
1SNA173627R2100
1SNA177812R1700
1SNA400819R0000
1SNA400818R0000
1SNA206394R0200
1SNA168401R0300
1SNA007865R2600
1SNA107239R0300
1SNA167860R0100
1SNA167927R1000
1SNA400826R0000
1SNA199421R1600
1SNA199423R1000
1SNA199437R1600
1SNA199439R2000
1SNA199433R1200
1SNA199435R1400
1SNA291833R1700
1SNA291301R0200
1SNA215999R2100
1SNA291311R2300
1SNA215580R2100
1SNA199417R1200
1SNA199476R2500
1SNA116771R2000
1SNA399678R2700
1SNA290358R2500
1SNA399679R2000
1SNA290360R2300
1SNA291559R0400
1SNA291560R0100
1SNA116964R1200
1SNA116965R1300
1SNA199336R2000
1SNA399758R2700
1SNA199352R0000
1SNA199354R0200
1SNA199382R2700
1SNA290281R0100
1SNA400825R0000
1SNA117318R2300
1SNA117668R0200
1SNA117600R0300
1SNA216114R1200
1SNA296114R1300
1SNA116713R1600
1SNA116977R1700
1SNA118368R1600
1SNA400824R0000
1SNA118499R2300
1SNA400273R1700
1SNA116951R1500
1SNA215266R0100
1SNA113067R1700
1SNA199341R0500
1SNA114434R0500
1SNA116987R0200

141
129
142
130
131
96
96
96
96
102
248
186
262
196
177
181
169
161
248
57
168
170
182
140
150
139
149
140
150
186
128
164
128
114
28
49
196
203
199
205
201
232
236
216
225
26
40
33
52
57
127
181
116
120
119
106
107
102
104
230
177
260
262
121
170
101
263
65
64

D2.8.N.ADO
D2.8.P.ADO
D2.8.SFDT.ADO2
D2.8.SFLT.ADO2
D2.8.SFT.ADO2
D2.8.SNNT.ADO2
D2.8.SNT2.ADO
D55.FF
D27.AF
D27.FF
D6.A.LLP
D6.A.NTLP
D6.ADO
D6.ADO.2
D6.ADO.4
D6.D1.P.ADO
D6.D2.ADO
D6.D2.N.ADO
D6.LL
D6.LLP
D6.LNTP1
D6.LNTP2
D6.LNTP3
D6.LNTP4
D6.LNTP6
D6.LNTP7
D6.LNTP8
D6.N.ADO
D6.NLP
D6.NTLP
D6.P.ADO
D6.SN.ADO
D6.SNT2.ADO
D8.ADO
D8.D2.P.SF
D8.D2.P.SFD
D8.D2.P.SFL
D8.N.ADO
D8.P.ADO
D8.SF.I.ADO
D8.SFDT2.I.ADO
D8.SFDT2.I.ADO2
D8.SFLT2.I.ADO
D8.SFLT2.I.ADO2
D8.SFT2.I.ADO
D8.SFT2.I.ADO2
D8.SN.ADO
D8.SNNT2.I.ADO
D8.SNNT2.I.ADO2
D10.SNBTB1
D10.SNBTB2
D8.ADO
D8.ADO.2
D8.ADO.4
D8.ADO3EL6
EL61
ENS.FE-BCP
ENS.FEDBCP
EV6I
EV8S
FC2
FC2.MC
FC4
FC4-1
FE2CPE
FEAD1
FEAD2
FEAD3
FEAD4
FEAD5
FEAD6
FECPE.2ADO
FED1.LFED10S1FED2.LFED2-4FED2AD1FED2AD2
FED3E
FED5.C3.ADO
FED5.C3.L
FED5.C4.ADO
FED5.C4.L
FED5.L.A
FED5.L.B
FED6
FEDA6
FEDAD1
FEDAD10
FEDAD4
FEDAD5
FEDAD7
FEDB.L
FEDCP
FEDR5
FEDR51
FEDR61
FEET80
FEM12F
FEM13F
FEM6
FEM6D
FEM8D2S1
FEM8S
FEM8T6FEM9FEMAD3
FEMR10FEMR8PAGE 269

14

IndexType classification
Type

Order code

Page

Type

Order code

Page

Type

Order codePage

FEMR8T
FEMS6
FEMS8
FEMSTA
FEMT1
FEMT2
FEMT3
FEMT4
FEMT5
FU520

1SNA116991R0600
1SNA113885R0100
1SNA114195R0600
1SNA116979R2100
1SNA113137R0200
1SNA113629R2700
1SNA114328R2200
1SNA114778R0500
1SNA116781R1300
1SNA008288R1500
1SNA008289R1600
1SNA008290R1300
1SNA008291R0000
1SNA008292R0100
1SNA179694R0300
1SNA179825R2600
1SNA125121R0600
1SNA165683R2200
1SNA115320R2700
1SNA115539R1700
1SNA115145R1400
1SNA115147R1600
1SNA115146R1500
1SNA125593R0000
1SNA165680R0300
1SNA115148R2700
1SNA115150R2500
1SNA115149R2000
1SNA125358R0300
1SNA165575R2500
1SNA115139R1600
1SNA115141R1000
1SNA115140R2300
1SNA199444R2500
1SNA199448R0100
1SNA199452R2500
1SNA199456R2100
1SNA115168R2300
1SNA115184R0400
1SNA115185R0500
1SNA115177R1400
1SNA115371R2600
1SNA115591R0400
1SNA115326R1100
1SNA115327R1200
1SNA125930R1500
1SNA125117R0200
1SNA115930R1300
1SNA115229R2000
1SNA115314R1500
1SNA115313R1400
1SNA115262R2100
1SNA115263R2200
1SNA115511R0300
1SNA400753R1000
1SNA115626R1600
1SNA115627R1700
1SNA125119R1400
1SNA115685R1200
1SNA115236R1700
1SNA115237R1000
1SNA115971R1000
1SNA115239R2200
1SNA115243R2600
1SNA115359R0200
1SNA105141R2700
1SNA105142R2000
1SNA115277R2000
1SNA115678R0200

67
112
113
162
168
161
165
162
166
262
121
262
262
121
49
246
229
239
65
166
90
94
86
230
240
91
95
87
231
241
88
92
84
245
246
247
248
256
257
258
259
253
254
260
255
63
227
63
66
165
165
102
102
102
102
103
104
228
64
157
158
159
160
161
162
168
168
168
67

M8.STP1
M8.STP3
M9.EE
M31.AF
M31.F
M31.FFMA2.5.D2-2CPE

1SNA115529R1500
1SNA115500R2500
1SNA115201R2500
1SNA115142R1100
1SNA115144R1300
1SNA115143R1200
1SNA125961R1000
1SNA400813R0000
1SNA400823R0000
1SNA125487R0600
1SNA125711R1500
1SNA400817R0000
1SNA400821R0000
1SNA400814R0000
1SNA400827R0000
1SNA400822R0000
1SNA400815R0000
1SNA105265R0300
1SNA115265R2400
1SNA115278R0100
1SNA115206R2200
1SNA146227R2500
1SNA179466R0600
1SNA178944R0400
1SNA163315R2600
1SNA290365R1400
1SNA290366R1500
1SNA290367R1600
1SNA113544R1200
1SNA167908R0600
1SNA113542R1000
1SNA399683R0500
1SNA399684R0600
1SNA399685R0700
1SNA399707R1500
1SNA399708R2600
1SNA399709R2700
1SNA113548R2600
1SNA163311R2200
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA163313R2400
1SNA173523R1100
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA113762R2400
1SNA173181R1300
1SNA163181R1100
1SNA290455R0700
1SNA238000R1600
1SNA229000R1500
1SNA231000R0700
1SNA230000R1200
1SNA233000R0100
1SNA232000R0000
1SNA234000R0200
1SNA237000R0500
1SNA236500R0600
1SNA163155R2600
1SNA235463R2300
1SNA196896R0000
1SNA199551R2000
1SNA103189R2600

167
168
101
89
93
85
180
180
181
226
178
178
179
176
176
177
182
112
112
113
197
197
263
263
166
201
201
201
182
116
182
205
205
205
205
205
205
248
260
248
248
248
168
262
168
168
168
161
161
161
161
96
166
65
186
231
114
226
236
263
225
262
149
102
107
96
49
41
225

SCDR61SCF6SCF9SCFCV1-2
SCFD
SCFEX1SCFEX3
SCFM6
SCFT1
SCFT2
SC-JB8-2
SC-JB8-3
SC-JB8-4
SFB1
SFB2
SPBO.NT.L
TGA8

1SNA173016R1000
1SNA118707R0300
1SNA103672R0100
1SNA116795R1100
1SNA114117R0700
1SNA103619R0400
1SNA103620R0100
1SNA114825R0500
1SNA103588R2600
1SNA114522R0500
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNA163860R0500
1SNA168956R0600
1SNA399886R2100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA400063R0000
1SNA128035R1600
1SNA128361R0100
1SNA163394R2600

119
66
102
113
225
240
240
240
168
161
170
170
170
232
232
236
262
262
262
186
231
230
65

ITVE
ITVE2
M10.NT
M10.PE.N
M10.RS
M10.ST-Sn
M35.AF
M35.F
M35.FF
M12.NT1
M12.PE.N
M42.AF
M42.F
M42.FF
M16.NT
M16.PE.N
M26.AF
M26.F
M26.FF
M6.D2.2S2
M6.D2.2S2.T
M6.D2.S1R
M6.D2.S1R.T
M6.DD
M6.DD1
M6.DE
M6.DE1M6.DE1.D
M6.DE1.D1
M6.DE2M6.DE2.D
M6.N.RS
M6.NT
M6.RS
M6.SNTS
M6.ST.Au
M6.ST.Sn
M12.FF

M13.FF
M13.FF.1
M8.NT
M8.RS
M8.ST
M8.ST1
M8.ST1.IP20
M8.ST3
M8.ST7
M8.STA
M8.STP

14

M8.STP.RS

MA2.5.D-2CPE
MA2.5.NT
MA2.5-2CPE
MA2.5-2CPE1-Pb
MA2.5-CPE
MA2.5-CPE.1
MA2.5-SNB-CPE
MS6
MS8
MTC6
MTC6.ExOUMAD
OUPAD
PC10-10PC5.34PC5-10PC51-10
PC5-2
PC52.10

PC52.66

PC6-10PC61-10
PC6-2
PC6-3
PC6-4
PC8-10PC81-10
PC8-2
PC8-3
PC8-4
PC8-R1
PC8-R2
PC8-R3
PC8-R4
PEP
PSC
PT101
RB-12W7
RC1010
RC410
RC510
RC55
RC610
RC65
RC810
RCAL85
RCT810
REH3
RPA
SCAD
SCAD5
SCD

INDUSTRIAL /// ENTRELEC - DEDICATED APPLICATIONS TERMINAL BLOCKSVRADO.CPE7
VRB3
VRB6
VSJ11

14
PAGE 271

RGW RING LUGTERMINAL BLOCKSStud technology
ENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSRGW Ring lug terminal blocks
Stud technology

Fast and secured wiring
for ring lugs
The RGW terminal blocks offer a combination of
fast and secured wiring.Thanks to its exceptional
design, the nuts are captive in a pivoting wing
and provide a convenient wiring of ring lugs.

RoHS

Speed up your processes
Fast ring lug connection- 45% faster than open style terminal blocks thanks

to captive and ready to tighten nuts
- No need to remove the nuts for the first use- Easy 3 steps wiring.

Security and protection
Secured wiring- 100% captive wire connection: optimal combinationof stud, safety wings, captive nut and ring lug- Self-locking wings to prevent sudden opening- Touch proof design.

Improve installation efficiency
Convenient installation- 15% more compact: save space on the DIN Rail versus open

style terminal blocks- Universal foot for mounting on symmetrical and asymmetri--15%

1SNC168020S0201

cal DIN Rails.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSFeatures
1

3

Safety wing withcaptive nut

Self-locking system

2

Vibration proof
connection

Universal
mounting footEasy 3 step wiring:
Open the safety wing - 2 Hook the wire on the stud and close the wing - 3 Screw down the nut

1SNC168021S0201

1

PAGE 3

2.5 mm2 14 AWG
Feed-through6 mm2 10 AWG
Feed-throughFeed-throughwith test sockets

Feed-throughwith test sockets

GroundGroundJumper bars
from 2 to 10 poles

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKS

Convenient circuit
separator
circuit & voltage
separation

1SNC168022S0201

RGW Ring lug terminal blocks
Stud technology - Range overview from 2.5 to 25 mm2 - 14 to 4 AWG

25 mm2 4 AWG
Feed-through6 mm 2 10 AWG
Feed-through with test sockets
Disconnect with sliding link

1SNC168022S0201

Easy CT short circuiting
with short-circuit plug

Convenient testing
test sockets compatible with
DIA 4 mm test plugs

PAGE 5

RGW Ring lug terminal blocks
Applications & certifications

Qualified for worldwide markets, applications
and for severe environments: vibration, shock...
Industry

Utility

HVAC

Ring lug technology is a long time approved technology in the industry (i.e semi
conductor production line) for it's provenreliability. The 100% captive connection
secures the wiring.

Thanks to a 100% captive connection our
RGW terminal blocks are well adapted
to the power, medium and low voltage
switchgear panels where a full securedconnection is required.

RGW terminal blocks are well adapted
to HVAC application requesting ring lug
terminals providing at the same time avibration proof connection and increased
productivity.

1SNC168023S0201

RoHS

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSRailway
Rail vehicles are subjected to extreme environmental
conditions. RGW terminal blocks are part of the
ENTRELEC railway terminal blocks offering, the largestof the market. RGW terminal blocks are tested inaccordance with the latest and most demanding
standards applying to rolling stock applications.

IEC 61373 Railway applications – Rolling stock equipment – Shock and vibration tests
RGW terminal blocks are complying with category 1 (body mounted) class B.
EN 45545-2 Railway applications. Fire protection on railway vehicles. Requirements forfire behavior of materials and components
RGW terminal blocks plastic materials are rated HL3 R22 (the highest Hazard level).
They can be used on vehicles for subway, tube, sleeping and couchette.
NF F 16-101 Directive relative to selecting materials in relation to their fire resistance interms of its behavior in a fire, the opacity of smoke and the toxicity of the gas released.
NF F 16-102 Complement to NF F 16-101. The purpose of this standard is to specify theapplication of NF F 16-101 to electrical equipment and especially to individual apparatus.
RGW terminal blocks plastic materials are rated I2F2. Level 3. This level concern products
mounted inside a room for passengers or running crew.
IEC 60068-2.1/IEC 60068-2.2/IEC 60068-2.78/IEC 60068-2.30 : Environmental test
RGW terminal blocks have successfully passed the damp heat, dry heat, cold climatic test.

1SNC168034S0201

UL94 (North America) Standard for Safety of Flammability of Plastic Materials for Parts in
Devices and Appliances testing
RGW terminal blocks plastic materials are rated UL94 V0.

PAGE 7

RGW2.5 Ring lug terminal blocks
Feed-through - 9 mm 0.354 in spacing
2.5 mm²
14 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168064V0014

Description
Feed-throughColorWith 2 studs M3 and captive nuts
in wings

54.7 2.15"

1SNA510003R0000

Pkg

Weightqty(1 pce) g

45

11.78

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

IEC
0.1 … 2.5 mm²
0.1 … 2.5 mm²

UL
26 ... 14 AWG

24 A

15 A
20 A
14 AWG

20 A

600 V

600 V

2.5 mm²
300 A
800 V
8000 V
IP10

CSA
26 ... 14 AWG

Rail
Nuts
Tool
Torque14 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 4 mmØ 0.157 in
0.6 ... 0.8 N.m
5.3 ... 7.1 lb.in
7 mm
0.28 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

47.2 1.86"

52 2.05"

RGW2.5-V0

Part Numbers

Mounting instructions

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

44.7 1.76"

Grey

Main technical data
Lugs

RGW2.5Type

22.4 0.88"

9 mm 0.354 in spacing

6

Accessories
1

Description

2
1
2
3

3

5

4
4
5

Color

End stops
10 mm
0.394 inEnd sections
1.2 mm
0.047 in
Lateral jumper bars 2 poles
24 A (IEC)3 poles
24 A (IEC)4 poles
24 A (IEC)
10 poles24 A (IEC)
Circuit separators 1.5 mm
0.059 inTerminal block
Blank marker
markers

Dark grey
Grey
Orange

Grey
White

Type

Part Numbers

BAM4
1SNK900001R0000
E-RGW2.5
1SNA519003R0000
PC-RG2.5-2
1SNA519103R0200
PC-RG2.5-3
1SNA519103R0300
PC-RG2.5-4
1SNA519103R0400
PC-RG2.5-10
1SNA519103R1000
CS-RGW-S
1SNA519200R0000
M-W610PC
1SNA235511R0600
MG-CPM-01 41090 1SNB041090R0510

Pkg

Weightqty(1 pce) g

50
25
25
20
15
5
25
360
1960

14.00
1.89
3.02
4.69
6.36
16.39
4.59
8.03
0.351

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description
GroundColorWith 2 studs M3 and captive
nuts in wings

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSGreen-yellow

Type
RGW2.5-PE-V0

Part Numbers
1SNA511003R0500

Pkg

Weightqty(1 pce) g

45

28.56

1SNC168024S0201

Ground Ring lug terminal blocks

RGW2.5-T Ring lug terminal blocks
Feed-through with test sockets - 9 mm 0.354 in spacing
2.5 mm²
14 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Ease your test operations with the 2 built-in nuts with test sockets compatible with DIA 2 mm 0.079 in,– Universal mounting on symmetrical and asymmetrical rails.

1SNC168064V0014

Ordering details
Description
Feed-throughColorWith 2 studs M3 and captive nuts
in wings

Type
Grey

RGW2.5-T-V0

Main technical data
Lugs
RGW2.5-T

54.7 2.15"

1SNA510103R0000

Pkg

Weightqty(1 pce) g

45

11.58

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 2.5 mm²
0.1 … 2.5 mm²

UL
26 ... 14 AWG

24 A

15 A
20 A
14 AWG

20 A

600 V

600 V

2.5 mm²
300 A
800 V
8000 V
IP10

CSA
26 ... 14 AWG

Rail
Nuts
Tool
Torque14 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 4 mmØ 0.157 in
0.6 ... 0.8 N.m
5.3 ... 7.1 lb.in
7 mm
0.28 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

47.2 1.86"

52 2.05"44.7 1.76"

Part Number

CE

RoHS

USR CNR

CSA

22.4 0.88"

9 mm 0.354 in spacing

Accessories
Description

2
1
2
3

3

5

4

6

4
5
6

Color

End stops
10 mm
0.394 inEnd sections
1.2 mm
0.047 in
Lateral jumper bars 2 poles
24 A (IEC)3 poles
24 A (IEC)4 poles
24 A (IEC)
10 poles24 A (IEC)
Circuit separators 1.5 mm
0.059 in
Test plugs
DIA 2 mm 0.079 in
Terminal block
Blank marker
markers

Dark grey
Grey
Orange

Grey
Black
White

Type

Part Number

BAM4
1SNK900001R0000
E-RGW2.5
1SNA519003R0000
PC-RG2.5-2
1SNA519103R0200
PC-RG2.5-3
1SNA519103R0300
PC-RG2.5-4
1SNA519103R0400
PC-RG2.5-10
1SNA519103R1000
CS-RGW-S
1SNA519200R0000
FC2.MC
1SNA107239R0300
M-W610PC
1SNA235511R0600
MG-CPM-01 41090 1SNB041090R0510

Pkg

Weightqty(1 pce) g

50
25
25
20
15
5
25
20
360
1960

14.00
1.89
3.02
4.69
6.36
16.39
4.59
1.00
8.03
0.351

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground Ring lug terminal blocks
Description
GroundColorWith 2 studs M3 and captive
nuts in wings

Green-yellow

Type
RGW2.5-PE-V0

Part Number
1SNA511003R0500

Pkg

Weightqty(1 pce) g

45

28.56

Technical data valid for copper conductors only.

PAGE 91SNC168025S0201

1

RGW6 Ring lug terminal blocks
Feed-through - 11 mm 0.433 in spacing
6 mm²
10 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168068V0014

Description
Feed-throughWith 2 studs M4 and captive nuts
in wings

Type
Grey

RGW6-V0

Main technical data
Lugs

RGW6

Part Numbers
1SNA510024R0000

Pkg

Weightqty(1 pce) g

40

19.76

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 6 mm²
0.1 … 6 mm²

UL
22 ... 10 AWG

41 A

30 A
30 A
10 AWG

30 A

600 V

600 V

6 mm²
720 A
800 V
8000 V
IP10

CSA
22 ... 10 AWG

Rail
Nuts
Tool
Torque10 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 ... 1.2 N.m
7.1 ... 10.6 lb.in
9.4 mm0.37 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

53.5 2.10"

61 2.40"44.7 1.76"

58 2.28"

Color

RoHS

USR CNR

CSA

22.35 0.88"

11 mm 0.433 in spacing

6

Accessories
1

Description

2
1
2
3

3

5

4

4
5

Color

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)7 poles
41 A (IEC)
10 poles
41 A (IEC)
Circuit separators 1.5 mm
0.059 inTerminal block
Blank marker
markers

Dark grey
Grey
Orange

Grey
White

Type

Part Numbers

BAM4
1SNK900001R0000
E-RGW6
1SNA519004R0000
PC-RG6-2
1SNA519104R0200
PC-RG6-3
1SNA519104R0300
PC-RG6-4
1SNA519104R0400
PC-RG6-7
1SNA519104R0700
PC-RG6-10
1SNA519104R1000
CS-RGW-S
1SNA519200R0000
M-W810PC
1SNA235510R0800
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

50
50
25
20
15
5
5
25
260
1120

14.00
2.65
3.44
5.40
7.33
13.24
19.05
4.59
0.27
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description
GroundColorWith 2 studs M4 and captive
nuts in wings

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSGreen-yellow

Type
RGW6-PE-V0

Part Numbers
1SNA511024R0500

Pkg

Weightqty(1 pce) g

40

31.76

1SNC168016S0201

Ground Ring lug terminal blocks

RGW6-T Ring lug terminal blocks
Feed-through with test sockets - 11 mm 0.433 in spacing
6 mm²
10 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Ease your test operations with the 2 built-in nuts with test sockets compatible with DIA 4 mm 0.157 in,– Universal mounting on symmetrical and asymmetrical rails.

1SNC168068V0014

Ordering details
Description
Feed-throughColorWith 2 studs M4 and captive nuts
in wings

Type
Grey

RGW6-T-V0

Main technical data
Lugs
RGW6-T

58 2.28"

1SNA510124R0000

Pkg

Weightqty(1 pce) g

40

19.04

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 6 mm²
0.1 … 6 mm²

UL
22 ... 10 AWG

41 A

30 A
30 A
10 AWG

30 A

600 V

600 V

6 mm²
720 A
800 V
8000 V
IP10

CSA
22 ... 10 AWG

Rail
Nuts
Tool
Torque10 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 ... 1.2 N.m
7.1 ... 10.6 lb.in
9.4 mm0.37 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

53.5 2.10"

61 2.40"44.7 1.76"

Part Number

CE

RoHS

USR CNR

CSA

22.35 0.88"

11 mm 0.433 in spacing

Accessories
Description

2
1
2
3

3

4

5

6

4
5
6

Color

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)7 poles
41 A (IEC)
10 poles
41 A (IEC)
Circuit separators 1.5 mm
0.059 in
Test plugs
DIA 4 mm 0.157 in
Terminal block
Blank marker
markers

Dark grey
Grey
Orange

Grey
White
White

Type

Part Number

BAM4
1SNK900001R0000
E-RGW6
1SNA519004R0000
PC-RG6-2
1SNA519104R0200
PC-RG6-3
1SNA519104R0300
PC-RG6-4
1SNA519104R0400
PC-RG6-7
1SNA519104R0700
PC-RG6-10
1SNA519104R1000
CS-RGW-S
1SNA519200R0000
FC4
1SNA167860R0100
M-W810PC
1SNA235510R0800
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

50
50
25
20
15
5
5
25
10
260
1120

14.00
2.65
3.44
5.40
7.33
13.24
19.05
4.59
10.00
0.27
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground Ring lug terminal blocks
Description
GroundColorWith 2 studs M4 and captive
nuts in wings

Green-yellow

Type
RGW6-PE-V0

Part Number
1SNA511024R0500

Pkg

Weightqty(1 pce) g

40

31.76

Technical data valid for copper conductors only.

PAGE 111SNC168019S0201

1

RGW25-M5 Ring lug terminal blocks
Feed-through - 18 mm 0.709 in spacing
25 mm²
4 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168067V0014

Description
Feed-through71.8 2.83"

Grey

RGW25-M5-V0

Part Numbers
1SNA510005R0000

Pkg

Weightqty(1 pce) g

10

49.10

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 25 mm²
0.1 … 25 mm²

UL
26 ... 4 AWG

101 A

85 A
115 A
4 AWG

100 A

600 V

600 V

25 mm²3000 A
800 V
8000 V
IP10

CSA
26 ... 4 AWG

Rail
Nuts
Tool
Torque

4 AWG
Max width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
3 ... 3.5 N.m
26.5 ...31 lb.in
16.2 mm0.64 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

64.3 2.53"

69 2.72"

60 2.36"

With 2 studs M5 and captive nuts
in wings

Type

Main technical data
Lugs

RGW25-M5

Color

30 1.18"

18 mm 0.709 in spacing

6

Accessories
1

3

4

1
2
3
4
5

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
101 A (IEC)
Circuit separators 2 mm
0.079 inTerminal block
Blank marker
markers

Color
Dark grey
Grey
Orange
Grey
White

Type

Part Numbers

BAZH1
1SNK900102R0000
E-RGW25
1SNA519005R0000
PC-RG25-2
1SNA519106R0200
CS-RGW-L
1SNA519201R0000
M-W1010PC
1SNA235512R1000
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

20
25
25
25
200
1120

24.00
0.146
8.81
13.72
0.10
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC168028S0201

5

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSRGW25-M6 Ring lug terminal blocks
Feed-through - 18 mm 0.709 in spacing
25 mm²
4 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168067V0014

Description
Feed-through71.8 2.83"

Grey

RGW25-M6-V0

Part Numbers
1SNA510006R0000

Pkg

Weightqty(1 pce) g

10

48.44

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 25 mm²
0.1 … 25 mm²

UL
26 ... 4 AWG

101 A

85 A
115 A
4 AWG

100 A

600 V

600 V

25 mm²3000 A
800 V
8000 V
IP10

CSA
26 ... 4 AWG

Rail
Nuts
Tool
Torque

4 AWG
Max width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
3.2 ... 3.5 N.m
28.3 ...32.7 lb.in
16.2 mm0.64 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

64.3 2.53"

69 2.72"

60 2.36"

With 2 studs M6 and captive nuts
in wings

Type

Main technical data
Lugs

RGW25-M6

Color

30 1.18"

18 mm 0.709 in spacing

6

Accessories

3

5

Description

2

4

1
2
3
4
5

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
101 A (IEC)
Circuit separators 2 mm
0.079 inTerminal block
Blank marker
markers

Color
Dark grey
Grey
Orange
Grey
White

Type

Part Numbers

BAZH1
1SNK900102R0000
E-RGW25
1SNA519005R0000
PC-RG25-2
1SNA519106R0200
CS-RGW-L
1SNA519201R0000
M-W1010PC
1SNA235512R1000
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

20
25
25
25
200
1120

24.00
0.146
8.81
13.72
0.10
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC168029S0201

1

Technical data valid for copper conductors only.

PAGE 13

RGW2.5-PE Ring lug terminal blocks
Ground - 10 mm 0.394 in spacing
2.5 mm²
14 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168066V0014

Description
GroundWith 2 studs M3 and captive nuts
in wings

Type

Green-yellow

RGW2.5-PE-V0

Main technical data

Part Number
1SNA511003R0500

CSA
26 ... 14 AWG

Rated cross section

2.5 mm²

14 AWG

14 AWG

Rated short-time withstand current (1s)Protection

300 A
IP10

NEMA 1

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rail
Nuts
Tool
TorqueRail connection screw
Tool

44.7 1.76"
54.7 2.15"

52 2.05"

Torque47.2 1.86"

Pkg

Weightqty(1 pce) g

45

28.56

Mounting instructions
IECUL
0.1 … 2.5 mm² 26 ... 14 AWG
0.1 … 2.5 mm²

Lugs

RGW2.5-PE

Color

Max width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 4 mmØ 0.157 in
0.6 ... 0.8 N.m
5.3 ... 7.1 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.5 ... 0.6 N.m
4.4 ... 5.3 lb.in
7 mm
0.28 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

22.4 0.88"

10 mm 0.394 in spacing

Accessories
1

Description

2
1
2
3

3

End stops
10 mm
0.394 inCircuit separators 1.5 mm
0.059 inTerminal block
Blank marker
markers

Color
Dark grey
Grey
White

Type

Part Number

BAM4
1SNK900001R0000
CS-RGW-S
1SNA519200R0000
M-W610PC
1SNA235511R0600
MG-CPM-01 41090 1SNB041090R0510

Pkg

Weightqty(1 pce) g

50
25
360
1960

14.00
4.59
8.03
0.351

1SNC168026S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSRGW6-PE Ring lug terminal blocks
Ground - 12 mm 0.472 in spacing
6 mm²
10 AWG

Description– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168069V0014

Description
GroundColorWith 2 studs M4 and captive nuts
in wings

Type

Green-yellow

RGW6-PE-V0

Main technical data

RGW6-PEUL
22 ... 10 AWG

Rated cross section

6 mm²

10 AWG

Rated short-time withstand current (1s)Protection

720 A
IP10

NEMA 1

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

CSA
22 ... 10 AWG

58 2.28"53.5 2.10"

Rail
Nuts
Tool

10 AWG

TorqueRail connection screw
Tool
Torque61 2.40"44.7 1.76"

1SNA511024R0500

Pkg

Weightqty(1 pce) g

40

31.76

Mounting instructions
IEC
0.1 … 6 mm²
0.1 … 6 mm²

Lugs

Part Number

Max width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 ... 1.2 N.m
7.1 ... 10.6 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.5 ... 0.8 N.m
4.4 ... 5.3 lb.in
9.4 mm0.37 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

22.35 0.88"

12 mm 0.472 in spacing

Accessories
1

Description

2
1
2
3

Dark grey
Grey
White

Type

Part Number

BAM4
1SNK900001R0000
CS-RGW-S
1SNA519200R0000
M-W810PC
1SNA235510R0800
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

50
25
260
1120

14.00
4.59
0.27
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC168017S0201

3

End stops
10 mm
0.394 inCircuit separators 1.5 mm
0.059 inTerminal block
Blank marker
markers

Color

Technical data valid for copper conductors only.

PAGE 15

RGW Ring lug terminal blocks
Stud technology - Test & measurement

Secure your measurement operations
With its 100% captive wire connection, RGW test & measurement
terminal blocks offer a safe and ergonomic test measurement
operation.
High performances– 6 mm² 10 AWG– 41 A (IEC) 30 A (UL)
– 1000 V (IEC) 600V (UL).

Features– Test sockets provided on every disconnect blocks RGW6-ST-1…
– Aligned feed-through version RGW6-R1… available for all types of schematics.

Typical measurement configuration
Common point on the transformers

Bill of material

CT's
P1

L1
P1

L2
L3

PT's

P1
S1

P2 S1

P2 S1

P2

CT's

S2

S2

S2

P

P

P

S

S

S

1

2

PT's

3

3

4

2

1

3

N

Description

Type

Order code

Qty needed

1 Terminal block

RGW6-ST-1-V0

1SNA512124R0000 6

32 Terminal block

RGW6-R1-V0

1SNA510224R0000 0

1

3 End section

E-RGW6-ST

1SNA519004R0100 1

1

4 Short-circuit plug

SCP12-2

1SNA519300R0200 3

0

CT’s

PT’s

Current inputs

Voltage inputs
Measuring devices(ie: meters, protection relays…)

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKS

1SNC168038S0201

NRGW6-ST-1 Ring lug terminal blocks
Test disconnect with sliding link - 11 mm 0.433 in spacing
Description

6 mm²

1SNC168071V0014

10 AWG– Stud terminal block for ring lug connection,– Integrated captive nuts in protective wings provide easy and secured connection,– Secure your disconnect operations with the disconnect sliding link operated with a standard screwdriver,– Ease your test operations with the 2 independent built-in test sockets compatible with DIA 4 mm 0.157 intest plugs,– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
Description
Disconnect

RGW6-ST-1

Color

Type

With 2 studs M4 and captive nuts
in wings

Grey

RGW6-ST-1-V0

Main technical data

58.5 2.30"

54 2.12"85.7 3.37"

61.5 2.42"

Lugs

1SNA512124R0000

Pkg

Weightqty(1 pce) g

25

33.66

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated voltage
Rated short-time withstand current (1s)
Impulse withstand voltage
ProtectionIEC
0.1 … 6 mm²
0.1 … 6 mm²

UL
22 ... 10 AWG

41 A

30 A
30 A
10 AWG
600 V

6 mm²
1000 V
720 A
8000 V
IP10

CSA
22 ... 10 AWG

Rail
Nuts
Tool

30 A
Torque10 AWG
600 V

NEMA 1

Disconnect device
Tool
TorqueMax width of lug

42.65 1.67"

11 mm 0.433 in spacing

Part Number

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 ... 1.2 N.m
7.1 ... 10.6 lb.in
Flat screwdriverØ 4 mmØ 0.157 in
0.5 ... 0.8 N.m
4.4 ... 5.3 lb.in
9.4 mm0.37 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

Accessories
Description

2
1
2
3

3

4

5

6

7

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)7 poles
41 A (IEC)
10 poles
41 A (IEC)
Circuit separators 2 mm
0.079 in
Test plugs
DIA 4 mm 0.157 in IP20
Short circuit plugs
Terminal block
Blank marker
markers

Type

Dark grey
Grey
Orange

Grey
Red
Black
White

Part Number

BAZH1
1SNK900102R0000
E-RGW6-ST
1SNA519004R0100
PC-RG6-2
1SNA519104R0200
PC-RG6-3
1SNA519104R0300
PC-RG6-4
1SNA519104R0400
PC-RG6-7
1SNA519104R0700
PC-RG6-10
1SNA519104R1000
CS-RGW-L
1SNA519201R0000
FC4-1
1SNA167927R1000
SCP12-2
1SNA519300R0200
M-W810PC
1SNA235510R0800
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

20
25
25
20
15
5
5
25
10
10
260
1120

24.00
5.18
3.44
5.40
7.33
13.24
19.05
13.72
11.00
0.27
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through Ring lug terminal blocks
Description
Feed-throughColorWith 2 studs M4 and captive
nuts in wings

Type
Grey

RGW6-R1-V0

Part Number
1SNA510224R0000

Pkg

Weightqty(1 pce) g

25

36.42

Technical data valid for copper conductors only.

PAGE 17

1SNC168018S0201

1

RGW6-R1 Ring lug terminal blocks
Feed-through - 11 mm 0.433 in spacing
Description

6 mm²– Stud terminal block for ring lug connection,– Feed-through with the same profile as disconnect terminal block RGW6-ST-1…,– Integrated captive nuts in protective wings provide easy and secured connection,– Universal mounting on symmetrical and asymmetrical rails.
1SNC168070V0014

10 AWG

Ordering details
Description
Feed-throughColorWith 2 studs M4 and captive nuts
in wings

Type
Grey

RGW6-R1-V0

Main technical data
RGW6-R1

Lugs

61.5 2.42"
53.5 2.11"

54 2.13"85.7 3.37"

Part Number
1SNA510224R0000

Pkg

Weightqty(1 pce) g

25

36.42

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 6 mm²
0.1 … 6 mm²

UL
22 ... 10 AWG

41 A

30 A
30 A
10 AWG

30 A

600 V

600 V

6 mm²
720 A
1000 V
8000 V
IP10

CSA
22 ... 10 AWG

Rail
Nuts
Tool
Torque10 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 ... 1.2 N.m
7.1 ... 10.6 lb.in
9.4 mm0.37 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

42.6 1.68"

11 mm 0.433 in spacing

Accessories
1

Description

2
1
2
3

3

4

5

6

7

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)7 poles
41 A (IEC)
10 poles
41 A (IEC)
Circuit separators 2 mm
0.079 in
Test plugs
DIA 4 mm 0.157 in IP20
Short circuit plugs
Terminal block
Blank marker
markers

Type

Dark grey
Grey
Orange

Grey
Red
Black
White

Part Number

BAZH1
1SNK900102R0000
E-RGW6-ST
1SNA519004R0100
PC-RG6-2
1SNA519104R0200
PC-RG6-3
1SNA519104R0300
PC-RG6-4
1SNA519104R0400
PC-RG6-7
1SNA519104R0700
PC-RG6-10
1SNA519104R1000
CS-RGW-L
1SNA519201R0000
FC4-1
1SNA167927R1000
SCP12-2
1SNA519300R0200
M-W810PC
1SNA235510R0800
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

20
25
25
20
15
5
5
25
10
10
260
1120

24.00
5.18
3.44
5.40
7.33
13.24
19.05
13.72
11.00
0.27
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description
Disconnect

Color
With 2 studs M4 and captive
nuts in wings

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKS

Type
Grey

RGW6-ST-1-V0

Part Number
1SNA512124R0000

Pkg

Weightqty(1 pce) g

25

33.66

1SNC168027S0201

Disconnect Ring lug terminal blocks

End sections
Terminal blocks accessories

E-RGW2.5 end sections
Description
1SNC160465V0014– End section compatible with RGW2.5... and RGW2.5-T... terminal block

Ordering details
Description

Color

1.2 mm 0.047 in spacing

Type
Grey

E-RGW2.5

Part Number
1SNA519003R0000

Pkg

Weightqty(1 pce) g

25

1.89

E-RGW2.5

E-RGW6 end sections
Description
1SNC160466V0014– End section compatible with RGW6... and RGW6-T... terminal block

Ordering details
Description

Color

1.4 mm 0.0551 in spacing

Type
Grey

E-RGW6

Part Number
1SNA519004R0000

Pkg

Weightqty(1 pce) g

50

2.65

E-RGW6

1SNC160467V0014

E-RGW6-ST end sections
Description– End section compatible with RGW6-ST-1… and RGW6-R1... terminal block

Ordering details
Description

Color

1.4 mm 0.0551 in spacing

Type
Grey

E-RGW6-ST

Part Number
1SNA519004R0100

Pkg

Weightqty(1 pce) g

25

5.18

E-RGW6-ST

E-RGW25 end sections
1SNC160468V0014

Description– End section compatible with RGW25... terminal block

Ordering details
Description

Color

1.4 mm 0.0551 in spacing

Type
Grey

E-RGW25

Part Number
1SNA519005R0000

Pkg

Weightqty(1 pce) g

25

0.146

E-RGW25

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-40 ... +100 °C-40 ... +100 °C-25 ... +70 °C-40 ... +212 °C-40 ... +212 °C-13 ... +167 °C

CE

1SNC168035S0201

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 19

Jumper bars
Terminal block accessories

1SNC160469V0014

Lateral jumper bars
Description– Lateral jumper bar for ring lug terminal block,– Allow the connection of consecutive blocks,– Compatible with RGW terminal block.

Ordering details
PC-RG2.5

Description

Color

Compatible with M3 stud. For blocks RGW2.5…
9 mm
0.354 in
2 poles
24 A (IEC)3 poles
24 A (IEC)4 poles
24 A (IEC)
10 poles24 A (IEC)
Compatible with M4 stud. For blocks RGW6…
11 mm
0.433 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)7 poles
41 A (IEC)
10 poles
41 A (IEC)
Compatible with M5 or M6 stud. For blocks RGW25…
18 mm
0.709 in
2 poles
101 A (IEC)

TypePart Number

Pkg

Weightqty(1 pce) g

Orange

PC-RG2.5-2
PC-RG2.5-3
PC-RG2.5-4
PC-RG2.5-10

1SNA519103R0200
1SNA519103R0300
1SNA519103R0400
1SNA519103R1000

25
20
15
5

3.02
4.69
6.36
16.39

Orange

PC-RG6-2
PC-RG6-3
PC-RG6-4
PC-RG6-7
PC-RG6-10

1SNA519104R0200
1SNA519104R0300
1SNA519104R0400
1SNA519104R0700
1SNA519104R1000

25
20
15
5
5

3.44
5.40
7.33
13.24
19.05

Orange

PC-RG25-2

1SNA519106R0200

25

8.81

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-40 ... +100 °C-40 ... +100 °C-25 ... +70 °C-40 ... +212 °C-40 ... +212 °C-13 ... +167 °C

All the main technical data provided are "manufacturer" values.
RoHS

1SNC168036S0201

CE

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSCircuit separators
Terminal blocks accessories

CS-RGW circuit separators
1SNC160471V0014

Description– Circuit separator for RGW terminal blocks,– Ease the visual identification of the several circuits within the terminal block assemblies,– Compatible with all RGW terminal blocks.

Ordering details
Description

Color

2 mm 0.078 in spacing

CS-RGW-L

Type
Grey

CS-RGW-L

Part Number
1SNA519201R0000

Pkg

Weightqty(1 pce) g

25

13.72

CS-RGW circuit separators
1SNC160470V0014

Description– Circuit separator for RGW terminal blocks,– Ease the visual identification of the several circuits within the terminal block assemblies,– Compatible with RGW feed-through and ground terminal blocks up to 11 mm 0.433 in spacing.

Ordering details
Description
1.5 mm 0.059 in spacing

Type
Grey

CS-RGW-S

Part Number
1SNA519200R0000

Pkg

Weightqty(1 pce) g

25

4.59

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-40 ... +100 °C-40 ... +100 °C-25 ... +70 °C-40 ... +212 °C-40 ... +212 °C-13 ... +167 °C

All the main technical data provided are "manufacturer" values.
CE

RoHS

1SNC168037S0201

CS-RGW-S

Color

Technical data valid for copper conductors only.

PAGE 21

RGW Ring lug terminal blocks
RGW Accessories

Markers and marking systems
Marking systems

Support platesMarkers

Type

Part Number

TypePart Number

Type

MG3 KIT

1SNB419001R0000

MG2-QTB 991011

1SNB991011R0000

MG-CPM-01 41090 1SNB041090R0510
MG-CPM-01-41096 1SNB041096R0810

SPRC 26

1SNA360036R0300

M-W610PC
M-W810PC
M-W1010PC

1SNA235511R0600
1SNA235510R0800
1SNA235512R1000

1SNC168039S0201

AMS 600 KIT
1SNA360000R2400
AMS 250 BASIC KIT 1SNA360000R2500

Part Number

INDUSTRIAL /// ENTRELEC - RGW RING LUG TERMINAL BLOCKSDBL
POWER
DISTRIBUTION BLOCKSENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKSDBL power distribution blocks

The clever distribution concept
The exclusive compact and modular design of our power distribution
blocks allows easy installation combined with a great flexibility of use.

RoHS

Easy to install
3 configurations in 1 product:
Single pole splitter: split of power main input into several outputs
Multiple poles splitter: interlocking function and ready to use
marking kit (L1, L2, L3, N, PE, +, - ) delivered with each blockGrouping: of several inputs into 1 output (solar application).
Flexible cover facilitates identification & wiring:- Reversible, two directions opening, snap-on- All wiring data’s and specifications visible on top.

SplitterSingle poleGroup

Multiple pole

L1

L2

L3

Space saving
Panel space saving:
Save up to 50 % rail space compare to conventional distribution
bars thanks to our modular compact design.
1 500 V DC:
Voltage rating adapted to most recent solar inverters requirements.

Bus bar

DBL

Increased productivity
Reduced wiring, inventories, hardware and assembly costs:- Reduce assembly time by 80 % compared to conventional
systems- Our modular and touch proof concept eliminates the needs
for bus bars, isolators, fasteners, protection screens…
- Accept aluminum & copper conductors- 1 product in stock for 3 possible configurations.

50%

space saving

1500 V DC%-8s0embly
1SNC166009S0201 - Rev. D

as timeINDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKSDBL power distribution blocks
1 product, 2 applications
Distributing power in industrial and commercial panels HVAC, machinery, power distribution
unit (PDU), commercial panel
3 Phases
DBL80, DBL125, DBL160, DBL175, DBL250, DBL400,
DBL125-3, DBL175-C-3

3 Phases for flat conductor
DBL250-F, DBL500-F

L1

L1

L2

L2

L3

L3

3 Phases with jumpering wire
DBL80, DBL125, DBL160, DBL175, DBL400-PV, DBL125-3,
DBL175-C-3 and DBL500-22

2 in/2 out configuration
DBL500-22

L1

L1

L2
L3

Combining PV strings in one single output
PV combiner box, central inverter in a solar power plant

1SNC166027S0201 - Rev. C

Up to 12 PV strings
DBL80…DBL500-F
DBL400-PV specifically designed for solar application with 12 inputs of 16 mm².

PAGE 3

DBL power distribution blocks
Screw clamp technology
Range overview 1000 V AC / 1500 V DC (IEC) - 1000 V (UL), from 80 to 550 A

Single pole
DBL80
7 connections

DBL1258 connections

DBL160
8 connections

DBL17512 connections

DBL250 and
DBL40012 connections

Panel or
DIN rail mounting
Easy blockassemblythanks to theinterlocking piece

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

Easy jumpering
Increase the number of
outputs by connecting
two blocks together

Pre-printed markers(L1, L2, L3, N, PE, +, -)delivered with eachblockSolarThree poles

Flat conductor

2 in/2 out

DBL400-PV
14 connections

DBL125-3 andDBL175-C-3
8x3 connections

DBL250-F and
DBL500-F
7 and 12 connections

DBL500-22
4 connections

Flat conductor feed-in
Combiningof 12 photovoltaic strings
to collect solar energy up to1500 V DC (IEC), 1000 V DC (UL)

Flexible cover foreasy wiring:• Two directions opening• Removable & snap-on

Main technical data
printed on the cover andvisible from top

PAGE 5

1SNC166011S0201 - Rev. B

x3

DBL power distribution blocks
Panorama

Single pole
Input/ Output
Round conductors

7

Number of connections
Max current
IEC

80 A

16 mm²4 AWG-

16 mm²-

Cu 125 A

115 A

35 mm²

2 AWG

Al

-

35 mm²-

Cu 160 A

160 A

70 mm²

2/0 AWG

Al-

70 mm²-135 A

Cu 175 A

175 A

70 mm²

2/0 AWG

Al-

70 mm²-135 A

Cu 250 A

255 A

120 mm²

250 KcmilAl-

120 mm²-

200 A

Cu 400 A

335 A

185 mm²

400 KcmilAl-

185 mm²-

Cu 500 A

510 A

95 mm²250 Kcmil

Cu 550 A

400 A

95 mm²250 Kcmil

300 A

12

12

12

UL

Al

100 A

8

Cross section

Cu 80 A
63 A

8

DBL80
DBL125
DBL160
DBL175
DBL250
DBL400Flat conductors

Input:
Flat conductors
Output:Round conductors

Number of connections
Max current

7

12

Max cross section

IEC

UL

Cu 250 A

250 A

15.5 x 7.5 mm

Cu 500 A

420 A

24 x 10 x 1 mm

DBL250-F

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKSDBL500-F

Three poles

8x3
x3

x3

X3

8x3

2 in/2 out

Solar

4

14

X3

DBL125-3

DBL175-C-3

DBL500-22

1SNC166026S0201 - Rev. B

DBL400-PV

PAGE 7

DBL80 power distribution blocks
Single pole - 28.4 mm 1.11 in spacing
Description

1SNC166026V0014• 3 configurations: distribute unipolar and multipolar power lines, or combine several inputs• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Increase the number of outputs by using the optional input and connecting two DBL together• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

Ordering details
Description
Feed-throughSingle pole distribution, 7
connections

Color

Type

Part Number

Pkg Weightqty

1 pce g

Grey

DBL80

1SNL308010R0000

170

Main technical data
Connecting capacity
Max current / Cross section

16.7
0.66"

59.2 2.33"
51.7 2.04"

50.2 1.98"

25.7 1.01"
18.2 0.72"

DBL80

IEC
80 A / 16 mm²
63 A / 16 mm²1000 V AC / 1500 V DC
8 kV
1920 A

CopperAluminium

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
Protection

UL
80 A / 4 AWG
1000 V

100 kA
27 kA
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com
36.3 1.43"
CE

66 2.6"
5 0.2"
10.7
0.42"

14.8
0.58"

28.4 1.12"

53 2.09"11.5 x 5.5 mm
0.45 x 0.22"

9.5 x 5.5 mm
0.37 x 0.22"

CB

RoHS

USR

CSA

EAC

BV

Mounting & wiring instructions
TH 35-7.5,
TH 35-15

Rail
Connection
NumberWire type

Wire stripping length

Tool

Torque

Size

Input

28.4 mm 1.11 in spacing

Mounting instructions
5.5 mm 0.22"
PZ2

Ø 6.6 mm
Ø 0.26 inØ 4.5 mm
Output4 x
Ø 0.18 in
3 x

Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 6 mm²
14 ... 10 AWG

2.5 ... 16 mm²
14 ... 4 AWG
2.5 ... 6 mm²
14 ... 10 AWG

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

5.5 mm0.22 in
4 mm
0.16 in

15 mm
0.59 in
11 mm
0.43 in

1.5 ... 2 Nm
13.5 ... 18 lb.in
0.8 ... 1.2 Nm
7.2 ... 10.8 lb.in

Rigid Stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

4 mm 0.16"
PZ1

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

1SNC166012S0201

Accessories

DBL125 power distribution blocks
Single pole - 28.2 mm 1.11 in spacing
Description

1SNC166027V0014• 3 configurations: distribute unipolar and multipolar power lines, or combine several inputs• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Increase the number of outputs by using the optional input and connecting two DBL together• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

Ordering details
Description
Feed-throughSingle pole distribution, 8
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL125

1SNL312510R0000

1122

Main technical data
Connecting capacity
Max current / Cross section

50.7 2"

23.5
0.93"

59.8 2.35"
52.3 2.06"

32.5 1.28"
25 0.98"

DBL125

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
ProtectionCE

75 2.95"
62 2.44"

5 0.2"

10.7
0.42"

14.7
0.58"

28.2 1.11"

UL
115 A / 2 AWG
1000 V

100 kA
30 kA
IP20NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

36.3 1.43"

9.5 x 5.5 mm
0.37 x 0.22"

IEC
125 A / 35 mm²
100 A / 35 mm²1000 V AC / 1500 V DC
8 kV4200 A

CopperAluminium

12 x 5.5 mm
0.47 x 0.22"

CB

RoHS

EAC

BV

TH 35-7.5,
TH 35-15

Rail
Connection
NumberWire type

Wire stripping length

Tool

Torque

Size

Input

Mounting instructions

Ø 9.8 mm
Ø 0.39 inØ 6.8 mm
Output1 x
Ø 0.27 inØ 6.4 mm6 x
Ø 0.25 in

3 mm 0.12"

CSA

Mounting & wiring instructions

28.2 mm 1.11 in spacing

4 mm 0.16"

USR

1 x

10 ... 35 mm²
8 ... 2 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

10 ... 35 mm²
8 ... 2 AWG
6 ... 16 mm²
10 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

4 mm
0.16 in
3 mm
0.12 in
5.5 mm0.22 in

15 mm
0.59 in
11 mm
0.43 in
11 mm
0.43 in

3.5 ... 5 Nm
31 ... 44 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

When using maximum cable size with insulated ferrules, use a maximum of 2 non-adjacent holes in each row.
Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

5.5 mm 0.22"
PZ2

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

PAGE 91SNC166013S0201

Accessories

DBL125-3 power distribution blocks
3x1 pole - 84.6 mm 3.33 in spacing
Description

1SNC166049V0014

x3• The usage of three poles distribution block is recommended for L1, L2, L3 applications• Each pole can be separated from the assembly to align the poles with upstream equipment configuration• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

X3

Ordering details
Description
Feed-throughThree poles distribution block 3x8
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL125-3

1SNL312530R0000

1

367

Main technical data
Connecting capacity
Max current / Cross section

23.5
0.93"

50.7 2"59.8 2.35"
52.3 2.06"

32.5 1.28"
25 0.98"

DBL125-3

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
ProtectionCE

75 2.95"===

5 0.2"=

62 2.44"

CB

1000 V

30 kA
IP20NEMA 1

=
=

10.7

0.42"

12 x 5.5 mm
0.47 x 0.22"

84.6 mm 3.33 in spacing

Mounting instructions

RoHS

USR

CSA

EAC

Mounting & wiring instructions
TH 35-7.5,
TH 35-15

Rail

14.7
0.58"

84.6 3.33"

28.2 1.11"

UL
115 A / 2 AWG

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

36.3 1.43"

9.5 x 5.5 mm
0.37 x 0.22"

IEC
125 A / 35 mm²
100 A / 35 mm²1000 V AC / 1500 V DC
8 kV4200 A

CopperAluminium

Connection
Numberby poleWire type

Wire stripping length

Tool

TorqueSize

Input
Ø 9.8 mm
Ø 0.39 inØ 6.8 mm
Output1 x
Ø 0.27 inØ 6.4 mm6 x
Ø 0.25 in
1 x

10 ... 35 mm²
8 ... 2 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

10 ... 35 mm²
8 ... 2 AWG
6 ... 16 mm²
10 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

4 mm
0.16 in
3 mm
0.12 in
5.5 mm0.22 in

15 mm
0.59 in
11 mm
0.43 in
11 mm
0.43 in

3.5 ... 5 Nm
31 ... 44 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

When using maximum cable size with insulated ferrules, use a maximum of 2 non-adjacent holes in each row.
Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

5.5 mm 0.22"
PZ2
3 mm 0.12"
4 mm 0.16"

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

1SNC166020S0201

Accessories

DBL160 power distribution blocks
Single pole - 28.2 mm 1.11 in spacing
Description

1SNC166028V0014• 3 configurations: distribute unipolar and multipolar power lines, or combine several inputs• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Increase the number of outputs by using the optional input and connecting two DBL together• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

Ordering details
Description
Feed-throughSingle pole distribution, 8
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL160

1SNL316010R0000

1120

Main technical data
Connecting capacity
Max current / Cross section

50.7 2"

23.5
0.93"

59.8 2.35"
52.3 2.06"

32.5 1.28"
25 0.98"

DBL160

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
ProtectionCE

75 2.95"
62 2.44"

5 0.2"

10.7
0.42"

14.7
0.58"

28.2 1.11"

UL
160 A / 2/0 AWG
1000 V

100 kA
30 kA
IP10NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

36.3 1.43"

9.5 x 5.5 mm
0.37 x 0.22"

IEC
160 A / 70 mm²
135 A / 70 mm²1000 V AC / 1500 V DC
8 kV6000 A

CopperAluminium

12 x 5.5 mm
0.47 x 0.22"

CB

RoHS

EAC

BV

TH 35-7.5,
TH 35-15

Rail
Connection
NumberWire type

Wire stripping length

Tool

Torque

Size

Input

Mounting instructions

Ø 11.8 mm
Ø 0.46 inØ 6.8 mm
Output1 x
Ø 0.27 inØ 6.4 mm6 x
Ø 0.25 in

3 mm 0.12"

CSA

Mounting & wiring instructions

28.2 mm 1.11 in spacing

5 mm 0.2"

USR

1 x

16 ... 50 mm²
6 ... 1/0 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

16 ... 70 mm²
6 ... 2/0 AWG
6 ... 16 mm²
10 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

5 mm
0.20 in
3 mm
0.12 in
5.5 mm0.22 in

18 mm
0.708 in
11 mm
0.43 in
11 mm
0.43 in

6... 10 Nm
53 ... 88 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

When using maximum cable size with insulated ferrules, use a maximum of 2 non-adjacent holes in each row.
Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

5.5 mm 0.22"
PZ2

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

PAGE 111SNC166014S0201

Accessories

DBL175 power distribution blocks
Single pole - 46.2 mm 1.82 in spacing
Description

1SNC166029V0014• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Increase the number of outputs by using the optional input and connecting two DBL together, or increase
the current rating with two wires, 300 A with 50 mm² wires and 350 A with 2/0 AWG wires• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

Ordering details
Description
Feed-throughSingle pole distribution, 12
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL175

1SNL317510R0000

1200

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
Protection

23.5
0.93"

61.3 2.41"
53.8 2.12"

Connecting capacity
Max current / Cross section

52.3 2.06"

DBL17532.5 1.28"
25 0.98"

Main technical dataCECB

61 2.4"100 kA
30 kA
IP10NEMA 1

RoHS

USR

CSA

EAC

BV

TH 35-7.5,
TH 35-15

23.5
0.93"

17.6 14.9
0.69" 0.59"

Rail
46.2 1.82"

1000 V

Mounting & wiring instructions

72.5 2.85"

11.5 x 5.5 mm
0.45 x 0.22"

10.5 x 5 mm
0.41 x 0.2"

UL
175 A / 2/0 AWG

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

30.4 1.2"

4.7 0.19"

IEC
175 A / 70 mm²
135 A / 70 mm²1000 V AC / 1500 V DC
8 kV6000 A

CopperAluminium

46.2 mm 1.81 in spacing

Mounting instructions
5 mm 0.2"

Connection
NumberWire type

Wire stripping length

Tool

TorqueSize

Input
Ø 11.8 mm
Ø 0.46 inØ 6.4 mm
Output10 x
Ø 0.25 in
2 x

10 ... 50 mm²
8 ... 1/0 AWG
2.5 ... 16 mm²
14 ... 6 AWG

10 ... 70 mm²
6 ... 2/0 AWG
2.5 ... 16 mm²
14 ... 6 AWG

5 mm
0.20 in
5.5 mm0.22 in

15 mm
0.708 in
11 mm
0.43 in

6... 10 Nm
53 ... 88 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

When using maximum cable size with insulated ferrules, use a maximum of 3 non-adjacent holes in each row.
Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

5.5 mm 0.22"
PZ2

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

1SNC166015S0201

Accessories

DBL175-C-3 power distribution blocks
3x1 pole - 84.6 mm 3.33 in spacing
Description

1SNC166050V0014

x3• The usage of three poles distribution block is recommended for L1, L2, L3 applications• Each pole can be separated from the assembly to align the poles with upstream equipment configuration• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

X3

Ordering details
Description
Feed-throughThree poles distribution block 3x8
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL175-C-3

1SNL317531R0000

1360

Main technical data
Connecting capacity
Max current / Cross section

23.5
0.93"

50.7 2"59.8 2.35"
52.3 2.06"

32.5 1.28"
25 0.98"

DBL175-C-3

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
ProtectionCE

75 2.95"===

5 0.2"=

62 2.44"

CB

1000 V

30 kA
IP10NEMA 1

=
=

10.7

0.42"

12 x 5.5 mm
0.47 x 0.22"

84.6 mm 3.33 in spacing

Mounting instructions

RoHS

USR

CSA

EAC

Mounting & wiring instructions
TH 35-7.5,
TH 35-15

Rail

14.7
0.58"

84.6 3.33"

28.2 1.11"

UL
175 A / 2/0 AWG

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

36.3 1.43"

9.5 x 5.5 mm
0.37 x 0.22"

IEC
175 A / 70 mm²
135 A / 70 mm²1000 V AC / 1500 V DC
8 kV6000 A

CopperAluminium

Connection
Numberby poleWire type

Wire stripping length

Tool

TorqueSize

Input
Ø 11.8 mm
Ø 0.46 inØ 6.8 mm
Output1 x
Ø 0.27 inØ 6.4 mm6 x
Ø 0.25 in
1 x

16 ... 50 mm²
8 ... 1/0 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

16 ... 70 mm²
6 ... 2/0 AWG
6 ... 16 mm²
10 ... 6 AWG
2.5 ... 16 mm²
14 ... 6 AWG

18 mm
0.708 in
11 mm
0.43 in
11 mm
0.43 in

5 mm
0.20 in
3 mm
0.12 in
5.5 mm0.22 in

6... 10 Nm
53 ... 88 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

When using maximum cable size with insulated ferrules, use a maximum of 2 non-adjacent holes in each row.
Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

5.5 mm 0.22"
PZ2
3 mm 0.12"
5 mm 0.16"

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

PAGE 13

1SNC166021S0201

Accessories

DBL250 power distribution blocks
Single pole - 46 mm 1.81 in spacing
Description• 3 configurations: distribute unipolar and multipolar power lines, or combine several inputs• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

1SNC166030V0014

Ordering details
Description
Feed-throughSingle pole distribution, 12
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL250

1SNL325010R0000

1

439

Main technical data
Connecting capacity
Max current / Cross section

60 2.36"

69 2.72"
61.5 2.42"

27.3 1.07"
25.8
1.02"

34.8 1.37"

DBL250

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
ProtectionCE1000 V

100 kA
51 kA
IP10NEMA 1

CB

RoHS

USR

CSA

EAC

BV

Mounting & wiring instructions

84.5 3.33"

TH 35-7.5,
TH 35-15

29.5
1.16"

Rail
46 1.81"UL
255 A / 250 Kcmil

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

37.2 1.46"
96 3.78"IEC
250 A / 120 mm²
200 A / 120 mm²1000 V AC / 1500 V DC
8 kV11400 A

CopperAluminium

Connection
Number
5.4 x 7.6 mm
0.21 x 0.3"

46 mm 1.81 in spacing

Wire type

6 mm 0.24"

Tool

TorqueInput
Ø 15.3 mm
Ø 0.60 inØ 8.7 mm2 x
Ø 0.34 in
OutputØ 6.4 mm5 x
Ø 0.25 inØ 5.7 mm4 x
Ø 0.22 in
1 x

Mounting instructions

Wire stripping length

Size

Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

35 ... 95 mm²
2 ... 3/0 AWG
2.5 ... 25 mm²
14 ... 4 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 10 mm²
14 ... 8 AWG

35 ... 120 mm²
2 ... 250 Kcmil
2.5 ... 35 mm²
14 ... 2 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 10 mm²
14 ... 8 AWG

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

28 mm
1.10 in
11 mm
0.43 in
11 mm
0.43 in
11 mm
0.43 in

6 mm
0.24 in
4 mm
0.16 in
3 mm
0.12 in
3 mm
0.12 in

19 ... 21 Nm
168 ... 185 lb.in
3.5 ... 5 Nm
31 ... 44 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

4 mm 0.16"
3 mm 0.12"

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

1SNC166016S0201

Accessories

DBL250-F power distribution blocks
Single pole - Flat entry - 29 mm 1.14 in spacing
Description• Suitable for distributing power from flat conductors: flexible or solid bars
• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

1SNC166052V0014

Ordering details
Description
Feed-throughSingle pole distribution - Flat entry, 7
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL250-F

1SNL325060R0000

1119

Main technical data
Connecting capacity
Max current / Cross section

59.8 2.35"
52.3 2.06"

20.2
0.79"

50.7 2"29.2 1.15"
21.7 0.85"

DBL250-F

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
Protection

CE

11.1
0.44"

5 0.2"

15.1
0.59"

29 1.14"62 2.44"

12 x 5.5 mm
0.47 x 0.22"

UL
250 A / 6 x 15.5 x 0.8 mm
160 A / 12 x 4 mm
1000 V

100 kA
22.8 kA
IP20

USR

RoHS

NEMA 1

CSA

EAC

BV

Mounting & wiring instructions
TH 35-7.5,
TH 35-15

Rail
Connection
Number

9.5 x 5.5 mm
0.37 x 0.22"

IEC
250 A / 6 x 15.5 x 0.8 mm
208 A / 12 x 4 mm
1000 V AC / 1500 V DC
8 kV11400 AThe connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

36.3 1.43"
75 2.95"

Flexible busbar
Solid busbar

Wire type

Wire stripping length

Tool

Torque

Size

Input

29 mm 1.14 in spacing

1 x

15.5 x 7.5 mm
0.59 x 0.28 in

12 x 4 mm

3 x 9 x 0.8 mm ...
... 6 x 15.5 x 0.8 mm

15 mm
0.59 in

5 mm
0.20 in13.5 Nm
120 lb.in

6 x

Ø 6.6 mm
Ø 0.26 in

2.5 ... 16 mm²
14 ... 6 AWG

2.5 ... 16 mm²
14 ... 6 AWG

11 mm
0.43 in

5.5 mm0.22 in

2 ... 3 Nm
18 ... 26.5 lb.in

Mounting instructions
Output5 mm 0.2"

When using maximum cable size with insulated ferrules, use a maximum of 2 non-adjacent holes in each row.
Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

Solid busbar

Flexible busbar

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

5.5 mm 0.22"
PZ2

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

PAGE 15

1SNC166022S0201

Accessories

DBL400 power distribution blocks
Single pole - 46 mm 1.81 in spacing
Description• 3 configurations: distribute unipolar and multipolar power lines, or combine several inputs• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

1SNC166031V0014

Ordering details
Description
Feed-throughSingle pole distribution, 12
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL400

1SNL340010R0000

1425

Main technical data
Connecting capacity
Max current / Cross section

60 2.36"

69 2.72"
61.5 2.42"

27.3 1.07"
25.8
1.02"

34.8 1.37"

DBL400

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
ProtectionCE1000 V

100 kA
51 kA
IP10NEMA 1

CB

RoHS

USR

CSA

EAC

BV

Mounting & wiring instructions

84.5 3.33"

TH 35-7.5,
TH 35-15

29.5
1.16"

Rail
46 1.81"UL
335 A / 400 Kcmil

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

37.2 1.46"
96 3.78"IEC
400 A / 185 mm²
300 A / 185 mm²1000 V AC / 1500 V DC
8 kV
18000 A

CopperAluminium

Connection
Number
5.4 x 7.6 mm
0.21 x 0.3"

46 mm 1.81 in spacing

Wire type

8 mm 0.31"

Tool

TorqueInput
Ø 18.8 mm
Ø 0.74 inØ 8.7 mm2 x
Ø 0.34 in
OutputØ 6.4 mm5 x
Ø 0.25 inØ 5.7 mm4 x
Ø 0.22 in
1 x

Mounting instructions

Wire stripping length

Size

Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

95 ... 150 mm²
3/0 ... 300 Kcmil
2.5 ... 25 mm²
14 ... 4 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 10 mm²
14 ... 8 AWG

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

95 ... 185 mm²
3/0 ... 400 Kcmil
2.5 ... 35 mm²
14 ... 2 AWG
2.5 ... 16 mm²
14 ... 6 AWG
2.5 ... 10 mm²
14 ... 8 AWG

Rigid Solid(IEC V-U class 1, UL solid)

28 mm
1.10 in
11 mm
0.43 in
11 mm
0.43 in
11 mm
0.43 in

8 mm
0.31 in
4 mm
0.16 in
3 mm
0.12 in
3 mm
0.12 in

25 Nm
221 lb.in
3.5 ... 5 Nm
31 ... 44 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

4 mm 0.16"
3 mm 0.12"

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

1SNC166017S0201

Accessories

DBL400-PV power distribution blocks
Single pole - 46 mm 1.81 in spacing
Description

1SNC166053V0014• Suitable for solar application with the possibility to combine 12 photovoltaic strings• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Increase the number of outputs by using the optional input and connecting two DBL together• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

Ordering details
Description
Feed-throughSingle pole distribution, 14
connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL400-PV

1SNL340011R0000

1202

Main technical data
Connecting capacity
Max current / Cross section

69 2.71"61.5 2.42"

26.8
1.06"

60 2.36"35.8 1.41"
28.3 1.11"

DBL400-PV

CopperRated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
Protection

IEC
550 A / (2x) 95 mm²

UL
400 A / (2x) 250 Kcmil

1000 V AC / 1500 V DC
8 kV
22800 A

1000 V

100 kA
47.88 kA
IP10

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com
44.18 1.74"
CE

103 4.06"

CB

RoHS

USR

CSA

EAC

BV

Mounting & wiring instructions
TH 35-7.5,
TH 35-15

Rail
18.8
0.74"

46 1.81"92.8 3.65"

Ø 5.4 x 7.6 mm
0.21" x 0.3"

Connection
NumberWire type

Wire stripping length

Tool

Torque

Size

Input

46 mm 1.81 in spacing

Mounting instructions
6 mm 0.24"

Ø 15,5 mm
Ø 0.59 inØ 6.6 mm
Output12 x
Ø 0.26 in
2 x

Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

25 ... 95 mm²
4 … 3/0 AWG
2.5 ... 16 mm²
14 ... 6 AWG

25 ... 120 mm²
4 ... 250 Kcmil
2.5 ... 16 mm²
14 ... 6 AWG

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

6 mm
0.24 in
3 mm
0.19 in

28 mm
1.1 in11 mm
0.43 in

19 ... 21 Nm
168 … 185 lb.in
2 ... 3 Nm
18 ... 26.5 lb.in

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

3 mm 0.12"

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

PAGE 17

1SNC166024S0201

Accessories

DBL500-22 Power Distribution Blocks
Single pole - 46 mm 1.81 in spacing
Description

1SNC166054V0014• Suitable for distributing or connecting main power lines with 2 inputs and 2 outputs• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Increase the number of outputs by using the second input and connecting two DBL together• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

Ordering details
Description
Feed-throughSingle pole distribution, 4connections

Color

Type

Part Number

Pkg Weightqty

1 pce gGrey

DBL500-22

1SNL850001R0000

1224

Main technical data
Connecting capacity
Max current / Cross section

69 2.71"61.5 2.42"

26.8
1.06"

60 2.36"35.8 1.41"
28.3 1.11"

DBL500-22

CopperRated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
Protection

IEC
500 A / (2x) 95 mm²

UL
510 A / (2x) 250 Kcmil

1000 V AC / 1500 V DC
8 kV
22800 A

1000 V

100 kA
47.88 kA
IP10

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com
44.2 1.74"
CE

103 4.06"

CB

RoHS

USR

CSA

EAC

BV

Mounting & wiring instructions
TH 35-7.5,
TH 35-15

Rail
18.8
0.74"

46 1.81"92.8 3.65"

Ø 5.4 x 7.6 mm
0.21" x 0.3"

Connection
NumberWire type

Wire stripping length

Tool

Torque

Size

Input

46 mm 1.81 in spacing

Mounting instructions

6 mm 0.24"

Ø 15.5 mm
Ø 0.61 inØ 15.5 mm
Output2 x
Ø 0.61 in
2 x

Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

25 ... 95 mm²
4 ... 3/0 AWG
25 ... 95 mm²
4 ... 3/0 AWG

25 ... 120 mm²
4 ... 250 Kcmil
25 ... 120 mm²
4 ... 250 Kcmil

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

Rigid Solid(IEC V-U class 1, UL solid)

6 mm
0.24 in
6 mm
0.24 in

28 mm
1.1 in
28 mm
1.1 in19 ... 21 Nm
168 ... 185 lb.in
19 ... 21 Nm
168 ... 185 lb.in

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver1

Description

2
1

End Stops2

Terminal Block
Markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Dark Grey

Green
Blue
White

Pre-printed marker card
(L1-L2-L3-N-PE)

TypePart Number

Pkg

Weightqty

1 pce g

BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL

1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000

50
50
20
20
20

14.00
5.30
24.00
10.00
10.00

MC512PAMC512PA1SNK149999R0000
1SNK149002R0000

20
1

10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKS

1SNC166025S0201

Accessories

DBL500-F power distribution blocks
Single pole - Flat entry - 46 mm 1.81 in spacing
Description• Suitable for distributing power from flat conductors: 500A (IEC), 420A (UL)
• Mount it on Din rail or plate and save up to 50% rail space compared to conventional copper bars
• Reduce the assembly time by 80% by avoiding to use fastening and isolating components• Easy identification with the reversible cover and delivered pre-printed markers L1, L2, L3, N, PE, +, –.

1SNC166051V0014

Ordering details
Description

Color

Feed-throughSingle pole distribution - Flat entry, 12 Grey
connections

Type

Part Number

Pkg Weightqty

1 pce g

DBL500-F

1SNL350060R0000

1

514

Main technical data
Connecting capacity
Max current / Max cross section

69 2.72"
61.5 2.42"

27.8
1.09"

60 2.36"36.8 1.45"
29.3 1.15"

DBL500-F

Rated voltage
Rated impulse voltage
Short-time withstand current (Icw 1s)
Short Circuit Current Rating (SCCR)
Rated peak withstand current (Ipk)
Protection

CE

UL
420 A / 10 x 24 x 1 mm
420 A / 25 x 5 mm (x2)1000 V

28800 A
100 kA
43.9 kA
IP20

NEMA 1

USR

RoHS

CSA

EAC

Mounting & wiring instructions

92.8 3.65"

TH 35-7.5,
TH 35-15

Rail
Connection
Number

18.75
0.74"

46 1.81"IEC
500 A / 10 x 24 x 1 mm
500 A / 25 x 5 mm (x2)1000 V AC / 1500 V DC

The connecting capacity data for one Rigid: Solid/Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA
standards (Copper conductors). All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA
certificates and technical datasheet available on http://www.TE.com

44.2 1.74"
103 4.06"

Flexible busbar
Solid busbar

Ø 5.4 x 7.6 mm
0.21" x 0.3"

Wire type

Wire stripping length

Tool

Torque

Size

Input
1 x

46 mm 1.81 in spacing

12 x 4 mm up to(2x) 25 x 5 mm

3 x 9 x 0.8 mm …
... 10 x 24 x 1 mm

35 mm
1.38 in

5 mm
0.20 in13.5 Nm
119.5 lb.in

2.5 ... 25 mm²
14 ... 4 AWG
2.5 ... 10 mm²
14 ... 8 AWG
2.5 ... 16 mm²
14 ... 6 AWG

2.5 ... 35 mm²
14 ... 2 AWG
2.5 ... 10 mm²
14 ... 8 AWG
2.5 ... 16 mm²
14 ... 6 AWG

11 mm
0.43 in
11 mm
0.43 in
11 mm
0.43 in

4 mm
0.16 in
3 mm
0.12 in
3 mm
0.12 in

3.5 … 5 Nm
31 ... 44 lb.in
2 … 3 Nm
18 ... 26.5 lb.in
2 … 3 Nm
18 ... 26.5 lb.in
Flexible busbar

Rigid Solid(IEC V-U class 1, UL solid)

Solid busbar

Flexible with insulated ferrule(IEC V-K & UL: class 5/6)

26 x 10.8 mm
1.02 x 0.43 inMounting instructions
5 mm 0.2"

4 mm 0.16"

OutputØ 8.69 mm
Ø 0.34 inØ 5.7 mm4 x
Ø 0.22 inØ 6.59 mm
5 x
Ø 0.26 in
2 x

Not allowed
Flexible without ferrule(IEC V-K & UL: class 5/6)
Allen key

Rigid stranded(IEC V-R class 2, UL class B/C)

Posidriv - flat screwdriver

3 mm 0.12"

1

Description

2
1

End stops2

Terminal block
markers

Color
10 mm
5.2 mm
10 mm
Blank card

0.394 in
0.205 in
0.394 in

Pre-printed marker card
(L1-L2-L3-N-PE)

Dark grey

Green
Blue
White

Type
BAM4
BAZ1
BAZH1
MC512PA-GN
MC512PA-BL
MC512PAMC512PAPart Number
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK149002R0000

Pkg

Weightqty

1 pce g

50
50
20
20
20
20
1

14.00
5.30
24.00
10.00
10.00
10.00
10.00

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify the terminal
block's ratings: Complete information available in the accessories section of the catalog.

PAGE 19

1SNC166023S0201

Accessories

IndexPart Number/Type classification
Part Number

Type

Page

MC512PAMC512PA-GN
MC512PA-BL
MC512PA
BAM4
BAZ1
BAZH1

8
8
8
8
8
8
8

1SNL
1SNL308010R0000
1SNL312510R0000
1SNL312530R0000
1SNL316010R0000
1SNL317510R0000
1SNL317531R0000
1SNL325010R0000
1SNL325060R0000
1SNL340010R0000
1SNL340011R0000
1SNL350060R0000
1SNL850001R0000

DBL80
DBL125
DBL125-3
DBL160
DBL175
DBL175-C-3
DBL250
DBL250-F
DBL400
DBL400-PV
DBL500-F
DBL500-22

8
9
10
11
12
13
14
15
16
17
19
18

Type

Part Number

B
BAM4
BAZ1
BAZH1

Page

1SNK900001R0000
1SNK900002R0000
1SNK900102R0000

8
8
8

D
DBL80
DBL125
DBL125-3
DBL160
DBL175
DBL175-C-3
DBL250
DBL250-F
DBL400
DBL400-PV
DBL500-22
DBL500-F

1SNL308010R0000
1SNL312510R0000
1SNL312530R0000
1SNL316010R0000
1SNL317510R0000
1SNL317531R0000
1SNL325010R0000
1SNL325060R0000
1SNL340010R0000
1SNL340011R0000
1SNL850001R0000
1SNL350060R0000

8
9
10
11
12
13
14
15
16
17
18
19

M
MC512PAMC512PAMC512PA-BL
MC512PA-GN

1SNK149002R0000
1SNK149999R0000
1SNK149998R0000
1SNK149997R0000

8
8
8
8

1-1773959-2_Index_TE

1SNK
1SNK149002R0000
1SNK149997R0000
1SNK149998R0000
1SNK149999R0000
1SNK900001R0000
1SNK900002R0000
1SNK900102R0000

INDUSTRIAL /// ENTRELEC - DBL POWER DISTRIBUTION BLOCKSNotes

PAGE 21

ESSAILEC®
TEST BLOCKSENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSSummary

ESSAILEC® test blocks allow to safely and easily
perform test operations such as current andvoltage measurement, monitoring, injection,
repair or replacement of meters and protective
relays installed in secondary circuits of current
and voltage transformers or sensors.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSESSAILEC® test blocks
Overview 		

1/ 3

Current and voltage sensors application

2/ 9

Test principles - ESSAILEC RJ45		

10ESSAILEC RJ45 sockets for current and voltage sensors		

14

®

®

Current transformers application

16

ESSAILEC ® sockets for Current Transformers		

22

ESSAILEC ® pre-wired plugs for Current Transformers		

24

ESSAILEC universal adaptor with Ø 4mm outputs		

25

ESSAILEC customized plugs		

26®

Voltage transformers application

2

3/ 15

Test principles - ESSAILEC ® RJ45		

®

1

3

4

4/ 29

Make before break 			

30

Break before make			36

Closed contact			42

Independent circuits			

48

Pre-wired plugs			

49

Customized plugs			

51

Protection lids and covers

5/ 55

Multicircuits

6/ 56

Mounting instructions

7/ 57

5

6

7

Mounting instructions for coding 		58

Outer dimensions, mounting instructions 		

60

8/ 64

Summary

Index		

8

1-1773959-3_EN - Edition July 2019

PAGE 1

1

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSESSAILEC® test blocks

1

24

Continuous operation
7

Easy plug & play solution
ESSAILEC® allows a simultaneous test of 1 to 4 circuits
thanks to the combination of a plug and a socket.
Fast test operation
Thanks to make before break principle, the current
transformers short circuiting is automatically performed(no cursor or switch element to operate manually).
Current testing without cutting the energy supply.

Safety and protection
Operator's safety
IP20 protection for the socket and IP40 with the cover.
Sealing option available to prevent unauthorized access.
Error free systems
Coding system on plugs & sockets prevent from risksof mixing between various circuits.
Protection against reverse plug insertion.
Unitary traceability
Engraved on insulating body.

Easy to install
Multiple choice of mounting
5 possibilities to install ESSAILEC® on front, within the panel or ona plate.
Various choice of wiring technologies
ESSAILEC® offers several connection types: ring tongue, screw
clamp, quick-connect and RJ45, to allow different wire terminations and connections up to 10 mm².

1SNC169001S0201

ESSAILEC® test blocks allow tosafely and easily perform test
operations such as current andvoltage measurement, monitoring,
injection, repair or replacement ofmeters and protective relays installed
in secondary circuits of current andvoltage transformers or sensors.

PAGE 3

Features and benefits

ESSAILEC® is especially designed to fit the electricity utilities requirements for safeand reliable testing. The test operations can be made without any circuit break andwithout opening the panel door.
ESSAILEC® is approved by major utilities and successfully implemented for years inworldwide electricity production, transport and distribution networks.

1

ESSAILEC® operation principle

Socket designMake
beforebreak

ClosedIndependent

The sockets are available in the following designs:• Socket with "Make before break" contact design, available in thecurrent, voltage, and RJ45 ranges• Socket with "Break before make" (opened) contact design, available in voltage application• Socket with "Closed" contact design, available in voltage application• Socket with "4 independent circuits" for voltage application.

1SNC169002S0201

ESSAILEC® is based on a plug & play operation solution.
It is composed of a socket and a test plug.
The socket is installed in the circuit and wired to the device to betested during its installation or servicing (protection relay in switchboard or meters).
The plug is connected to the test set and allows measurement or
signal injection.

Breakbefore make(Opened)INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSSafety & protection

Color coding
Prevent from risks of mixing between various circuits.
Color coding: green for current applications, grey / orange / blue
for voltage applications.

IP20

IP40

1

Seal

Operator’s safety
Front protection IP20 for the socket and IP40 with the protective lid.
The protective lid is equipped with a sealing option to prevent
unauthorized access.

Locking mechanism
Secure the plug on the socket.
No risk of unplugging during test operations.

Error free systems thanks
to coding pins
Up to 6 possible combinations toallocate test plug with its appropriate
socket for circuit differentiation.

1SNC169002S0201

Unitary traceability
The socket integrates a permanent tracking number
engraved on insulating body.

Protection against reverse plug insertion
Socket and plug integrate a special plastic shape preventing the circuit polarities reversal.

PAGE 5

Features and benefits

Easy to install
Multiple choices of socket mounting

Mounting on panel: front or base mounting

Mounting within the panel.

1

Flush mounting

Half-base mounting

Base mounting

TH35 rail mounting

Rack mounting

Various choices of wiring technologies
ESSAILEC® offers several connection types (according
to the mounting selected): ring tongue, screw clamp,
quick‑connect and RJ45, to allow different wire terminations
and connections up to 10 mm².
Refer to sockets panorama page for more details.

Ring tongue

Quick-connect

Screw clamp

RJ45

Easy circuit identification
01, 02, 03, 04: equipment side.
Premarked block in two directions to allow convenient readingwhatever the mounting sense.

1SNC169002S0201

1, 2, 3, 4: transformers side.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSPlug
The plug is connected to the test equipment by means of test plugs.
Plugs are supplied in various configurations, either prewired or readyto be customized.

1
Universal plugwith Ø 4 mmdirect outputs
Plug with crimping pins forcustomization

Pre-assembled plug

2x4 poles plugs(8 contact pins)
Allow testing of 4 current or
voltage circuits.
Available in different colors(green, grey, orange, blue).

Pre-assembled plug

4 poles plugs(4 contact pins)
Allow testing of 4 voltage
circuits.
Available in different colors(grey, orange, blue).

Pre-assembled plug

1 pole plugs(2 contacts pins)
Allow testing of 1 current
or voltage circuit.
Available in different colors(red for current applications or
grey for voltage applications).

Plugs for customization

Plugs for customization
In order to provide more
flexibility to the end-users
ESSAILEC® plugs can becustomized according to thetargeted application(see customized plugs
catalog page).

Protection
Lid or Cover provide dust protection (IP40) and prevent unauthorized accessthanks to their embedded sealing option.
Lid and cover with electrical continuity, are necessary compatible with opened
contacts sockets (Break before make).
Thanks to their inner pins and linking bars they ensure the circuits continuity.

Cover

Lid withelectricalcontinuity

Cover withelectricalcontinuity

1SNC169002S0201

Lid

PAGE 7

Sockets panorama

Contact type

Mounting

Connection

For current andvoltage sensors

For current
transformers––

For voltage transformers
Grey coding(standard)Blue coding(polarity)

Orange coding(trip)

CC-E-VA

TC-E-VA

PC-E-VA–

CC-E-VA-6.6

TC-E-VA-2.2

PC-E-VA-8.8––

CC-E-VA-R2-6.6

TC-E-VA-R2-2.2

–

–

RJ45

TC-E-RJ45-INF

–

–

–

–

Quick connect––

TC-E-C5A-2.2––

Half-baseRing-tongue–

CC-D-VA

TC-D-VA

PC-D-VA–

Base/Half-baseScrew clamp––

TC-DS-VL

PC-DS-VL–

BaseScrew clamp–

CC-S-INF-VL-6.6

TC-S-INF-VL-2.2

–

–

TH35

Screw clamp–

CC-TH35-VL-6.6

TC-TH35-VL

–

–

Rack

Ring-tongue–

CC-R-VA–––

ReverseRing-tongue–

CC-I-VA-2

–

–

–

Flush

Ring-tongue––

TO-E-VA

PO-E-VADEO-E-VA––

TO-E-VA-12.12––

Half-baseRing-tongue––

TO-D-VA

PO-D-VA

DEO-D-VA

Base/Half-baseScrew clamp––

TO-DS-VL

PO-DS-VL–

BaseScrew clamp––

TO-S-INF-VL-12.12––

ReverseRing-tongue––

TO-I-VA-2

–

–

Flush

Ring-tongue––

TF-E-VA

PF-E-VA–

Half-baseRing-tongue––

TF-D-VA

PF-D-VA

DEF-D-VA

Base/Half-baseScrew clamp––

TF-DS-VL

PF-DS-VL–

BaseScrew clamp––

TT4-S-VL-INF––

1
Make before break

Break before makeOpened contact

Closed contact

Independent circuits

Flush

Ring-tongue

Socket designation

Circuit type
C: Current
T: Voltage
P: Polarity
DE: TripC

C

Mounting
E:
Flush
TH35:	Symmetricalrail TH35
DS:
Half-base / BaseD:
Half-base
S:
Base
R:
Rack
I:
ReverseP:
Connector style

-

E

VA

-

6.6

Connection
VA: Ring-tongue
VL: Screw clamp
C5A: Quick-connect
RJ45: RJ45 wire
1SNC169003S0201

Contacts
C: Make before break
O: Opened
F: Closed-

Coding6.6: Current
2.2: Voltage
8.8: Polarity
INF: With lid or coverØ:Without lid or cover

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Current and voltage sensors application
Make before break

2

10

ESSAILEC ® RJ45 sockets for current and voltage sensors

14

Summary_2

Test principles - ESSAILEC ® RJ45

PAGE 9Current and voltage sensors application
Make before break test principle - Measurement with ESSAILEC® RJ45 test plug

Test
equipment

RJ45 socket
TC-E-RJ45-INF

RJ45

RJ45 plug
FI-RJ45-DIA4

RJ45 plug

L1

L3
1

01

2

02

3

03

4

04

LPCT1

Test
equipment

LPVT1

RJ45 socket
RJ45
LPVT2

1

01

2

02

3

03

4

04

RJ45 socket

Testequipment

LPCT2

Protection relays

RJ45 plug

RJ45

RJ45 plug

LPCT3

LPVT3

LPCT : Low power current transducer (current sensor)
LPVT: Low power voltage transducer (voltage sensor)

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1

01

2

02

3

03

4

04

RJ45 socket

1SNC169004S0201

2

L2

RJ45

Calibrationequipment

Make before break base - Injection with ESSAILEC® RJ45 test plug

L2

L3

RJ45 plug

LPCT1

LPVT1

1

01

2

02

3

03

4

04

RJ45 socket
TC-E-RJ45-INF

2Protection relays

L1

RJ45 plug
FI-RJ45-DIA4

RJ45 socket

1SNC169004S0201

LPCT : Low power current transducer (current sensor)
LPVT: Low power voltage transducer (voltage sensor)

PAGE 11Current and voltage sensors application
Make before break test principle - With ESSAILEC® RJ45 test plug
Applications• Injection• Equipment replacement

1. Normal service

2. Lid removal

2

1.1 ESSAILEC® RJ45 sockets havea shielded body. The 3 sockets are
required to cover the testing operation on the 3 main lines (L1, L2, L3).

1.2 The lid is installed on thesocket and can be sealed to prevent unauthorized access.
The socket circuits are closed
and signals flow from current andvoltage sensors to protection relay.

The lid is removed.

2

Lidremoved4.2 Test phase: Injection

The RJ45 plug allows to perform injection. Plug a RJ45 connector on to the ESSAILEC® RJ45
plug to test the protection relay through the integrated RJ45 input.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1

NormalserviceMake before break base - Injection with ESSAILEC® RJ45 test plug

3. Preparation: Test plugs connections
3.2 The ESSAILEC® RJ45 test plug has
built-in dia. 4 (1) and RJ45 test sockets (2)in order to simplify the test operations. They
allow current and voltage sensors
measurement (1) as well as injection to theprotection relay (2).

2

2

1

3.1 The test equipment is equippedwith dia. 4 test plugs.

4. Test phase: Make before Break3

3
4

Preparation:
Test plugs
connections

4

When the plug is fully inserted
in the socket, inner mobile
contacts (3) are pushed downby plug’s plastic leads (4) andcircuits are opened. Signals arederived into the dia. 4 plug
towards the test set.
It is possible to perform
simultaneously current andvoltage sensors measurement.

4.1 Test phase: Measurement

Ex: Voltage sensors
measurement

1SNC169009S0201

Test phases
Measurement
Injection

Ex: Voltage and current
sensors measurement

PAGE 13Current and voltage sensors application
ESSAILEC® RJ45 sockets for current and voltage sensors - Make before break
Description
Dedicated for the use in Digital Switchgear including sensors (current or voltage):• RJ45 connection type (Cat.5),• Allow safe and easy measurement and injection operations,• Signals protection against EMI/RFI thanks to shielded lid on shielded socket,• Shielding tests according to IEC 62271-1 Annex J,• Grounding point: M5 screw to be wired with an adapted ring lug termination.
1SNC169160V0014

x4

Make before break principle:• The circuits are automatically disconnected with the insertion of the plug,• The circuits close automatically when the plug is removed.

Main technical data

TC-E-RJ45

2

Mounting instructions

Connecting capacity

IEC 947-1

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Accuracy
Storage temperature range
Working temperature range
Protection without lid / with lid

Polycarbonate UL94 V0
Silver-plated
125 V1000 V
3
1.5 A
0.5 %
-40 ... +85 °C-40 ... +85 °C
IP20 / IP40

Ordering details
Color

Type

Tool
(for grounding
screw)

Posidriv
Ø 4 mmØ 0.16 inTorque(for grounding
screw)

1.2 Nm10.8 lb.in

Compatible products
Part Number

Pkg Weight
qty 1 pce g

Lid / Cover

Plug

Socket

1SNA566000R0000

3138

Included

FI-RJ45-DIA4–

1SNA566001R0000

1

69.6

–

–

TC-E-RJ45-INF

SocketFlush mounting
Grey
TC-E-RJ45-INF

Plug
Grey

FI-RJ45-DIA4

Accessories

1

Description

Color

Type

Part Number

Protecting covers for RJ45 sockets

Grey

CPT-RJ45

1SNA167002R0000

For connection details, please refer to mounting instruction 1SNC169044L1701

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Pkg Weightqty (1 pce) g1
25.4

1SNC169010S0201

1

Current transformers application
Make before break

3

16

ESSAILEC ® sockets for Current Transformers

22

ESSAILEC ® pre-wired plugs for Current Transformers

24

ESSAILEC ® universal adaptor with Ø 4mm outputs

25

ESSAILEC ® customized plugs

26

Summary_3

Test principles

PAGE 15

Current transformers application
Make before break test principle

Test equipment

Measurement with 2x4 poles test plug

01
02
03
04
1
2
3
4

1

01

2

A

B

C

04

1

01

2

02

S1

3

03

S2

4

04

S1
S2

03

4

S1
S2

02

3

Protection relays, meters,
measurement, equipment

COR-C-R4-6.6

3

Injection or equipment replacement with 2x4 poles test plug

External
Short-circuiting
Injectionequipment

01
02
03
04

1

01

2
3

B

C

4

1

01

2

02

S1

3

03

S2

4

04

S1
S2

S1
S2

03
04

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169005S0201

A

Equipment

COR-C-R4-6.6

02

Make before break test principle

Injection or equipment replacement with 2x4 poles test plug (4 poles short-circuit)

01
02
03
04

Internal short-circuiting
Link (1, 2, 3, 4)

Injectionequipment

COR-C-R5-6.6

Automatic
CT short-circuiting
when plug-in
1

01

2

02

3

C

01

2

02

S1

3

03

S2

4

04

S1
S2

03

3

04

1

S1
S2

4

1SNC169005S0201

B

Equipment

A

PAGE 17

Current transformers application
Make before break test principle - With 2x4 poles test plug
Applications• Measurement on CT’s
• Injection• Equipment replacement

1. Normal service

3

1.1 ESSAILEC® current
sockets allow the simultaneous testing operations of 1 to 4 independent circuits on thesame socket.

2. Preparation: plug and lid

1.2 The lid is installed on thesocket and can be sealed toprevent unauthorized access. The socket circuits
are closed and signals flowfromcurrent transformers
to the equipment to betested.

2.1 The lid is removed.

2.2 Connect the ESSAILEC®
test plug leads to the test
set. (For equipment change
or injection, short-circuit
externally the 4 test leads connected on the current transformer side: 1-2-3-4)

2

Preparation

1

Normalservice

5. Back to normal service

5

Back tonormalservice

5.1 Plug removal closes back the socket
contacts and signals flow again throughthe socket.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

5.2 Lid is put back in place.

3. Test phase: Make

4.1 Measurement: Test phase - Break

1
3

2

1

COR-C-R4-6.6

During plug insertion, plug pins make contact with socket
pins (1). Contacts remain closed and the signal flow has
not change. This operation prevent signal
interruption (mandatory for current transformers).

When the plug is fully inserted in the socket, inner mobile contacts (2) are pushed down by plug’s plastic leads (3) and thefour circuits are opened simultaneously. Signals are derived
into the plug towards the test set without
interruption of continuity.

3

4.2 Injection or equipment
replacement: Test phase - Break3

Test phase:
Make

5

Injection

Short-circuited
4

Break

During preparation phase, the plug 4 test leads (1-2-3-4: current transformer side) have been short-circuitedexternally (4).
When the plug is fully inserted in the socket, the current
transformer is automatically short-circuited andcurrent injection (or equipment change) can be doneon the equipment side (5).
1SNC169011S0201

4

Test phase:

4

PAGE 19

Current transformers application
Make before break test principle - With 2x4 poles test plug (4 poles short-circuited)
Applications• Measurement on CT’s
• Injection• Equipment replacement

1. Normal service

3

1.1 ESSAILEC® current
sockets allow thesimultaneous testing operations of 1 to 4
independent circuitson the same socket.

2. Preparation: plug and lid

1.2 The lid is installed on 2.1
The lid is removed.
equipment side (1-2-3-4). The
socket and can be sealed toprevent unauthorized access. The socket circuits areclosed and signals flow fromcurrent transformers to theequipment to be tested.

2.1 The lid is removed.

2.2 Connect the ESSAILEC® test
plug leads to the test set.
This plug is equipped with a built-in
short-circuiting on
equipment side (1-2-3-4).

2

Preparation

1

Normalservice

5. Back to normal service

5

Back tonormalservice

5.1 Plug removal closes back the socket
contacts and signals flow again throughthe socket.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

5.2 Lid is put back in place.

3. Test phase: Make & CT short-circuiting

1

1

COR-C-R5-6.6

The plug is equipped with built in short circuited contacts on current transformers side (1-2-3-4)
During plug insertion, plug pins make contact with the socket pins (1), andsimultaneously the current transformer is short-circuited.

3

Test phase:Make

3

4. Test phase: Break and short-circuit(injection or equipment replacement)

Injection
5

4

4

3

Test phase:
Break

4.2 Current injection can be done on theequipment (5).

1SNC169012S0201

4.1 When the plug is fully inserted in the socket,
inner mobile contacts (3) are opened byplastic lead (4). The current transformer is
automatically short-circuited and circuits are
opened.

PAGE 21Current Transformers application
ESSAILEC® sockets for Current Transformers – Make before break
Description
Short-circuited type contacts for measurement, calibration and distribution applications.

1SNC169123V0014

x4

CC-E-VA

Main technical data

Mounting instructions

Connecting capacity
Screw clamp(VL)
Ring tongue(VA)

Rigid: Solid/Stranded
Flexible with insulated ferrule
Flexible with insulated ferruleØ lug hole size
Width

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range
Protection without lid / with lid
Coding color

IEC 947-1Rail

0.2 ... 6 mm²0.22 ... 4 mm²0.34 ... 10 mm²
3 mm
7.5 mmPolycarbonate
Gold-plated
400 V
4000 V
3
15 A
100 A/5 s ... 200 A/1 s-25 ... +70 °C-10 ... +55 °C
IP20 / IP40
Green

Screw clamp

Ordering details
TypePart Number

G32, TH 35-7.5,
TH 35-15

Wire
strippinglength

9.5 mm0.370 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 ... 0.8 Nm
4.4 ... 7.1 lb.in

Compatible products
Pkg Weight
qty

Lid

Cover

1 pce
g

Universal
plug

Pre-wired plugs
2x4 poles

4 poles

1 poleØ 4 mm

Ø 4 mm

Ø 4 mm

Ø 4 mmbayonetbayonetbayonetFlush mounting
Ring-tongue
CC-E-VA
1SNA166737R2000
CC-E-VA-6.6
1SNA166625R2000
CC-E-VA-R2-6.6 1SNA166976R0000

1
1
50

145
150
170

CPC-1 –
Lid +codingincluded

1

200

–

FIC-2/4-DIA4

COR-C-R4-6.6 COR-C-R5-6.6 COR-C-R3
COR-C-R1-6.6 COR-C-R2-6.6 COR-C-3

Base / Half-base mounting
Screw clamp
CC-S-INF-VL-6.6 1SNA166722R2100

Ring-tongue
CC-D-VA
1SNA166738R0100

Cover + FIC-2/4-DIA4
codingincluded

COR-C-R4-6.6 COR-C-R5-6.6 COR-C-R3
COR-C-R1-6.6 COR-C-R2-6.6 COR-C-3

1

90

CPC-1

–

FIC-2/4-DIA4

COR-C-R4-6.6 COR-C-R5-6.6 COR-C-R3
COR-C-R1-6.6 COR-C-R2-6.6 COR-C-3

1

114

CPC-1

included FIC-2/4-DIA4

COR-C-R4-6.6 COR-C-R5-6.6 COR-C-R3
COR-C-R1-6.6 COR-C-R2-6.6 COR-C-3

1

140

CPC-1

–

FIC-2/4-DIA4

–
–

–
–

COR-C-R3
COR-C-3

1

210

–

–

–

–
–

–
–

COR-C-R3
COR-C-3

TH35 rail mounting
Screw clamp
CC-TH35-VL-6.6 1SNA166963R0000

Rack mounting
Ring-tongue
CC-R-VA
1SNA166523R1200

Reverse mounting
Ring-tongue
CC-I-VA-2
1SNA166941R2500* compatible with CC-DS-VL socket only in "base" mounting option.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169016S0201

3

Make before break principle:• The circuit is automatically shorted with the insertion of the plug.
• The circuit closes automatically when the plug is removed.
• This system guarantees a complete safety.
• By convention, green coding is for current circuit.

Current Transformers application
ESSAILEC® sockets for Current Transformers – Make before break
Accessories

4

5

2

6

3

7

1
2
3
4
6
7
5

Description

TypePart Number

Interlocking peg
Mounting kits

CVABM
KEM-3
FX
KEM-1
PCVA
PCVL
BJ-VL

1SNA183436R0500
1SNA166962R0000
1SNA167682R2300
1SNA166928R2000
1SNA167496R1100
1SNA167681R2200
1SNA167680R0500

For 2 sockets assembly
For TH35 rail (a)For DIN 1 rail (a)For ring-tongue flush mounting (b)Lateral jumper bars Compatible with ring-tongue connection only (VA) (b)Compatible with screw connection only (VL); IP20 (c)Jumper bars
For two sockets screw connection type (c)Pkg Weight
qty 1 pce
g
10
0.4
10
24
10
20
50
18
10
1
10
1
10
1

(a) compatible with base mounting only.
(b) compatible with ring-tongue connection type socket only (VA).
(c) compatible with screw connection type socket only (VL).

Compatible products

3

Lid
CPC-1

Cover
CPC-7

Plug 2x4 poles bayonet
COR-C-R1-6.6

Plug 4 poles bayonet
COR-C-R2-6.6

Plug 1 pole bayonet
COR-C-3

Universal plug
FIC-2/4-DIA4

Plug 2x4 poles Ø 4 mm
COR-C-R4-6.6

Plug 4 poles Ø 4 mm
COR-C-R5-6.6

Plug 1 pole Ø 4 mm
COR-C-R3

Connection technologies

Ring-tongue

Screw clamp

1SNC169016S0201

1

PAGE 23Current Transformers application
ESSAILEC® pre-wired plugs for Current Transformers
Description• Standard current plugs are compatible with ESSAILEC® current sockets.
• Plugs are pre-wired with contact pins (BRE...) , coding, cables and test plugs assembled to ease your test
operations.

Main technical data
Connecting capacity

IEC 947-1

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range

Polycarbonate
Gold-plated
400 V
4000 V
3
15 A
100 A/5 s ... 200 A/1 s-25 ... +70 °C-10 ... +55 °C

Compatible
products

Ordering details
Description

TypePart Number

Pkg Weight
qty 1 pce g

Socket1 plug 2x4 pins / Green4 x Ø 4 mm test plugs / Black4 x Ø 4 mm test plugs / Red
Conductors section: 2.5 mm²
cable length: 2 m / 79"

COR-C-R4-6.6

1SNA167932R1500

1

1080

1 plug 2x4 pins / Green
4 bayonet security test plugs / Green
4 bayonet security test plugs / Red
Conductors section: 2.5 mm²
cable length: 2 m / 79"

COR-C-R1-6.6

1SNA166638R0500

1

1080

CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6

1 plug 2x4 pins with 4 short circuited pins
(1-2-3-4) / Green4 x Ø 4 mm test plugs / Black
Conductors section: 2.5 mm²
cable length: 2 m / 79"

COR-C-R5-6.6

1SNA167934R1700

1670

1 plug 2x4 pins with 4 short circuited pins
(1-2-3-4) / Green
1 bayonet security test plug / Green
1 bayonet security test plug / Grey
1 bayonet security test plug / Brown
1 bayonet security test plug / Yellow
Conductors section: 2.5 mm²
cable length: 2 m / 79"

COR-C-R2-6.6

1SNA166778R1100

1

670

1 plug 2 pins / Red
2 dia. 4 mm test plugs / Black

COR-C-R3

1SNA166979R0000

1320

1 plug 2 pins / Red
2 bayonet security test plugs / Yellow

COR-C-3

1SNA166643R0200

1

320

Plug 2x4 poles

Plug 4 poles
CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6

Plug 1 pole

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-R-VA
CC-I-VA-2
CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-R-VA
CC-I-VA-2

1SNC169017S0201

3

Current Transformers application
ESSAILEC® universal adaptor with Ø 4mm outputs

1SNC169154V0014

Description• Universal adaptor compatible with all ESSAILEC® current socket• It ensures quick and consistently reliable ESSAILEC® sockets tests• Ø 4 mm test plugs may be inserted directly without the need for extra accessories or tools. It is compatible
with all the insulated Ø 4mm test plugs available on the market
Standard current plugs are compatible with ESSAILEC® current sockets.
• Plugs are pre-wired with contact pins (BRE...) , coding, cables and test plugs assembled to ease your test
operations.

Main technical data
Connecting capacity

IEC 947-1

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range

Polycarbonate
Gold-plated
400 V
4000 V
3
15 A
100 A/5 s ... 200 A/1 s-25 ... +70 °C-10 ... +55 °C

FIC-2/4-DIA4

Ordering details

Compatible products

Description

TypePart Number

Pkg Weight
qty 1 pce g

Socket1

CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-R-VA

3

Universal plug
FIC-2/4-DIA4

Plug 2x4 pinswith direct insertion Ø 4 mm

20 0.78"

25 0.98"60

10.5 0.41"

01

01

01 01

1

1

1

AdaptorSocket63 2.48"

44 1.73"1SNA167937R0000

Dimensions (mm, inches)

1

Adaptor + socket

1SNC169018S0201

Electrical wiring for a socket with short-circuited contacts and anuniversal adaptor

For connection details, please refer to mounting instruction 1SNC169041L0201

PAGE 25

Current Transformers application
ESSAILEC® customized plugs
Description
Short-circuited type contacts for measurement, calibration and distribution applications.
Make before break principle:• The circuit is automatically shorted with the insertion of the plug.
• The circuit closes automatically when the plug is removed.
• This system guarantees a complete safety.
• By convention, green coding is for current circuit.

Ordering details
Description

TypePart Number

Pkg Weight
qty 1 pce g

Compatible
products
Socket1 pole plug with contact pins
Plug with 2x 2.5 mm² contact pins
(BRE-C-2.5), without coding pins.

FIC-2/1-1

1SNA166819R2300

1

27

CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-R-VA
CC-I-VA-2

Plugs without contact pins (contact pins BRE-C..., to be ordered separately)

3

1

2

Plugs 2x4 poles, long cover, with 2 coding
pins (COP-FI-1) and 8 locking pins.
Contacts pins (BRE-C...) to be ordered separately.

FIC-2/4-2

1SNA166936R1000

1

105

Plugs 2x4 poles, short cover, with 2 coding
pins (COP-FI-1) and 8 locking pins.
Contacts pins (BRE-C...) to be ordered separately.

FIC-2/4-1

1SNA166525R1400

191

Plug 2x4 poles, rack mounting R version, with 2coding pins (COP-FI-1) and 8 locking pins.
Contacts pins (BRE-C...) to be ordered separately.
Plug 2x4 poles, reverse mounting I version, with
2 coding pins (COP-FI-1) and 8 locking pins.
Contacts pins (BRE-C...) to be ordered separately.

FIC-2/4-R

1SNA166529R2000

180

CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-S-INF-VL-6.6
CC-D-VA
CC-TH35-VL-6.6
CC-R-VA

FIC-2/4-I

1SNA166589R2500

1

60

CC-I-VA-2

BRE-C-1
BRE-C-1.5
BRE-C-2.5
BRE-C-4
BRE-C-6

1SNA167264R0700
1SNA167265R0000
1SNA167260R1700
1SNA205876R0400
1SNA168146R0200

10
10
10
10
10

2.6
2.6
3
3
3

–
–
–
–
–

EXBR1
PSC
DLVR

1SNA167008R0300
1SNA173181R1300
1SNA167971R2400

1
1
10

24
478
0.4

–
–
–

FC4-1
FC4-5

1SNA167927R1000
1SNA167931R1400

10
10

11
10

–
–

FCB-1
FCB-2
CA

1SNA167690R0700
1SNA167692R2500
1SNA167697R2200

10
10
10

7
7
1.2

–
–
–

IR1
IR2
DI
IR3

1SNA167622R2600
1SNA167623R2700
1SNA167981R1700
1SNA167624R2000

5
5
10
10

15
35
7
6.4

–
–
–
–

COP-FI-1

1SNA167378R1100

10

2.3

–

BRE contact pins
Pin 1 mm²
Pin 1.5 mm²
Pin 2.5 mm²
Pin 4 mm²
Pin 6 mm²
Tools for contact pins
1 Pin extraction tool
2 Crimping tool for BRE pins 1 to 2.5 mm² (1)3 Locking sleeve for contact pin

dia 4 mm test plugs
3
4

4
5

IP20 with mobile protection
IP20 with permanent protection

6

6

7
8
9
10

Bayonet security test plug / Black
Bayonet security test plug / Red
7 Isolating cap for FCB plug
Accessories
8 Straight adaptor
9 H adaptor (short-circuit bridge)
10 Isolating cap for IR1 and IR2 adaptors
11 Adaptor between FCB plug and ring-tongue test
interface

Coding pins
12 Plug coding pin

1112(1) Refering to 1SNC169040D1702 to find other crimping tools

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169019S0201

Bayonet plugs

5

Current Transformers application
ESSAILEC® customized plugs
Pin installation on plugs

Locking pin, DLVR supplied withthe plug

BRE pin

1SNC169019S0201

3

PAGE 27

Summary_4

4

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Voltage transformers application

Make before break

30

Break before make

36
4

42

Independent circuits

48

Pre-wired plugs

49

Customized plugs

51

Summary_4

Closed contact

PAGE 29

Voltage transformers application
Make before break test principle

Simultaneous measurement and injection with 2x4 poles test plug

COR-T-R5-2.2

1

01

2

02

3

N

L1

L2

L3

03

4

04

1

01

2

02

3

03

4

04

Equipment

12
34Injectionequipment

Test equipment

01
02
03
04

4

Test equipment

Measurement with 2x4 poles test plug

1
2
3
4

Not used

1

COR-T-R5-2.2

L1

02

3

L2

L3

4

03
04

1

01

2

02

3

03

4

04
1SNC169006S0201

N

01

2

Equipment

01
02
03
04

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSMake before break test principle

Injection with 2x4 poles test plug

Not used

1

01

2

02

3

N

L1

L2

L3

4

03
04

1

01

2

02

3

03

4

04

4

1SNC169006S0201

COR-T-R5-2.2

Equipment

12
34Injectionequipment

01
02
03
04

PAGE 31Voltage transformers application
Make before break test principle - With 2x4 poles test plug
Applications• Measurement on VT’s
• Injection• Equipment replacement

1. Normal service

1.1 ESSAILEC® voltage sockets
allow the simultaneous
testing operations of 1 to 4 independent circuits on thesame socket.

4

2. Preparation: plug and lid

1.2 The lid is installed on thesocket and can be sealed toprevent unauthorized access. The socket circuits
are closed and signals flowfromcurrent transformers
to the equipment to betested.

2.1 The lid is removed.

2.2 Connect the ESSAILEC® test
plug leads to the test set.

2

Preparation

1

Normalservice

5. Back to normal service

5

Back tonormalservice

5.1 Plug removal closes back the socket
contacts and signals flow again throughthe socket.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

5.2 Lid is put back in place.

3. Test phase: Make

4.1 Measurement: test phase - Break

1
3

2

1
MeasureCOR-T-R5-2.2

During plug insertion, plug pins make contact with socket
pins (1). Contacts remain closed and the signals flow has
not changed.

3
Test phase:
Make

When the plug is fully inserted in thesocket, inner mobile contacts (2) arepushed down by plug’s plastic leads (3)and the four circuits are opened simultaneously. Signals are derived into theplug towards the test set. The equipment
to be tested is no more energized.

4

4.2 Injection or equipment
replacement: test phase - BreakInjection
4

4

Break

MeasureIn a second step or simultaneously, voltage injection can be done on the protection relay side (4).
1SNC169013S0201

Test phase:

PAGE 33

Voltage transformers application
ESSAILEC® sockets for voltage transformers - Make before break
Description
Short-circuited contacts for measurement, calibration and distribution applications.

1SNC169116V0014

x4

TC-E-VA

Make before break principle:• The circuit is automatically shorted with the insertion of the plug.
• The circuit closes automatically when the plug is removed.
• This system guarantees a complete safety.
• By convention grey coding is for voltage circuits and blue coding is for polarity circuits.

Main technical data

Mounting instructions

Connecting capacity
Rigid: Solid/Stranded
Flexible with insulated ferrule
Flexible with insulated ferruleØ lug hole size
Width
Flexible with insulated ferrule

Screw clamp(VL)
Ring tongue(VA)

Quick-connect
Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range
Protection without lid / with lid
Coding color

IEC 947-1Rail

0.2 ... 6 mm²0.22 ... 4 mm²0.34 ... 10 mm²
3 mm
7.5 mm2.5
Polycarbonate
Silver-plated
400 V
4000 V
3
8A
25 A/5 s ... 800 A/25 ms-25 ... +70 °C-10 ... +55 °C
IP20 / IP40
Grey
- BlueScrew clamp

Ordering details

Wire
strippinglength

9.5 mm0.370 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 ... 0.8 Nm
4.4 ... 7.1 lb.in

Compatible products
Pkg Weight
qty 1 pce g

Lid

1SNA166747R0200
1SNA166627R2200
1SNA166977R0000

1
1
50

140
150
150

–

PC-E-VA
PC-E-VA-8.8

1SNA166763R0200
1SNA166630R0100

1
1

145
200

CPT-1
Lid +
codingincluded
CPP-1
Lid +
codingincluded

Quickconnect
Grey
TC-E-C5A-2.2

1SNA166628R0300

1

170

Lid +
codingincluded–

1SNA166742R0500
1SNA166948R0400

1
1

100
170

CPT-1
–

COR-T-R5-2.2 COR-T-4-4 (2)COR-T-4-4

PC-DS-VL

1SNA166758R1500

1

130

CPT-1

CPT-5 (1) FI-2/4-DIA4
Cover +
codingincluded–Ring-tongue
Grey
TC-D-VABlue
PC-D-VA

1SNA166748R1300
1SNA166764R0300

1
1

147
115

CPP-1

–

FI-2/4-DIA4

COR-T-R5-2.2 COR-T-4-4 (2)COR-P-R1-8.8 –1SNA166964R0000

1

114

CPT-1

CPT-5

FI-2/4-DIA4

COR-T-R5-2.2 COR-T-4-4

Color

Type

Part Number

Cover

Universal
plug

Pre-wired plugs

FI-2/4-DIA4

COR-T-R5-2.2 COR-T-4-4

2x4 poles

4 poles

Flush mounting
Ring-tongue
Grey
TC-E-VA
TC-E-VA-2-2
TC-E-VA-R2-2.2
Blue

COR-P-R1-8.8 –FI-2/4-DIA4

COR-T-R5-2.2 COR-T-4-4

Base / Half-base mounting
Screw clamp
Grey
TC-DS-VL
TC-S-INF-VL-2.2

Blue

COR-P-R1-8.8 –TH35 rail mounting
Screw clamp
Grey
TC-TH35-VL(1) Compatible only in base mounting option.
(2) Compatible with some restrictions, please contact us.
Information on pre-wired plugs: Please refer to page "ESSAILEC® pre-wired plugs for voltage transformers".

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169020S0201

4

G32, TH 35-7.5,
TH 35-15

Voltage transformers application
ESSAILEC® sockets for voltage transformers - Make before break
Accessories

4

5

2

6

3

7

1
2
3
4
6
7
5

Description

TypePart Number

Interlocking peg
Mounting kits

CVABM
KEM-3
FX
KEM-1
PCVA
PCVL
BJ-VL

1SNA183436R0500
1SNA166962R0000
1SNA167682R2300
1SNA166928R2000
1SNA167496R1100
1SNA167681R2200
1SNA167680R0500

For 2 sockets assembly
For TH35 rail (a)For DIN 1 rail (a)For ring-tongue flush mounting (b)Lateral jumper bars Compatible with ring-tongue connection only (VA) (b)Compatible with screw connection only (VL); IP20 (c)Jumper bars
For two sockets screw connection type (c)

Pkg
qty
10
10
10
50
10
10
10

Weight1 pce g
0.4
24
20
18
1
1
1

(a) compatible with base mounting only.
(b) compatible with ring-tongue connection type socket only (VA).
(c) compatible with screw connection type socket only (VL).

Compatible products

Lid
CPC-1

Cover
CPC-7

4

Universal plugFI-2/4-DIA4

Plug 2x4 poles
COR-T-R5-2.2

Plug 4 poles
COR-T-4-4
Design for insertion 01-02-03-04

Connection technologies

Ring-tongue

Screw clamp

Quick-connect

1SNC169020S0201

1

PAGE 35

Voltage transformers application
Break before make test principle

Simultaneous measurement and injection with 2x4 poles test plug

COR-T-R5-2.2

1

01

2

02

3

N

L1

L2

L3

4

03
04

1

01

2

02

3

03

4

04

Equipment

12
34Injectionequipment

Test equipment

01
02
03
04

1SNC169007S0201

4

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSBreak before make test principle

Measurement or/and injection with 4 poles test plugs
FIT-1/4-D
Customized plug to be
wired by user.

1

01

2

02

3

N

L1

L2

L3

4

03
04

1

01

2

02

3

03

4

04

4

1SNC169007S0201

FIT-1/4-G

03
04

Equipment

3
4

01
02

Injectionequipment

Test equipment

1
2

PAGE 37

Voltage transformers application
Break before make test principle - With 2x4 or 4 poles test plug
Applications• Measurement on VT’s
• Injection• Equipment replacement

1. Normal service

2. Preparation: plug2

1.1 ESSAILEC® voltage sockets
allow the simultaneous testing operations of 1 to 4 independent circuits on the same socket.

41

1.2 The lid is installed on thesocket and can be sealed to prevent unauthorized access. The
socket has no mobile
contacts (closed style) (1).
Circuit continuity is ensured by thelid equipped with built- in contact
pins (2).

Connect the ESSAILEC® test
plug leads to the test set.

2

Preparation

1

Normalservice

5. Back to normal service

5

Back tonormalservice

5.1 When the plug is removed,
signals are disconnected.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

5.2 When lid is put back in place,signals flow again through thesocket.

3. Test phase: Break4. Simultaneous measurement and injection
Test phase: Make with 2x4 poles test plugs
Injection

MeasureMeasureCOR-T-R5-2.2

Removing of the lid opens the circuit.
The device to be tested is then isolated from the power supply (VT)and is no longer energized.

4.1 The plug is fully inserted in the socket, the signals are derived into the plug towards the test set.

4.2 While the plug is still in place simultaneous injection can be realized on the equipment.

4

OR

3

4. S
 eparated measurement and injection
Test phase: Make with 4 poles test plugs

Test phase:
Make

FIT-1/4-G
Design for
insertion 1-2-3-4

4Injection

COR-T-4-4
Design for
insertion 01-02-03-04

Test phase:
Break

4.1 The plug is fully inserted in thesocket, the signals are derived
into the plug towards the test set.

FIT-1/4-G
Design for
insertion 1-2-3-4

4.2 While the plug is still inplace, a second plug can be installed for injection on theequipment.

PAGE 39

1SNC169014S0201

MeasureVoltage transformers application
ESSAILEC® sockets for voltage transformers - Break before makeDescription
Opened type contacts for measurement and calibration applications.

1SNC169300V0014

x4

Break before make principle:• The connection is made thanks to the lid: the removing of the lid opens the circuit. So the device is isolated
from power supply to be tested.
• The circuit is closed only when the lid is reinstalled.
• By convention, grey coding is for voltage circuits blue coding is for polarity circuits and orange coding is fortrip circuits.

Main technical data

Mounting instructions

Connecting capacity

TO-E-VA

Rigid: Solid/Stranded
Flexible with insulated ferrule
Flexible with insulated ferruleØ lug hole size
Width

Screw clamp(VL)
Ring tongue
(VA)

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range
Protection without lid / with lid
Coding color

IEC 947-1Rail

0.2 ... 6 mm²0.22 ... 4 mm²0.34 ... 10 mm²
3 mm
7.5 mmPolycarbonate
Silver-plated
400 V
4000 V
3
8A
25 A/5 s ... 800 A/25 ms-25 ... +70 °C-10 ... +55 °C
IP20 / IP40
Grey
- Blue- Orange

Screw clamp

Ordering details

Wire
strippinglength

9.5 mm0.370 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 ... 0.8 Nm
4.4 ... 7.1 lb.in

Compatible products
Pkg Weight
qty 1 pce g

Lid

1SNA166743R0600

1

170

CPT-2

TO-E-VA-12.12

1SNA166925R1500

1

200

Blue

PO-E-VA

1SNA166759R1600

1

170

Lid +
codingincluded
CPP-2

OrangeDEO-E-VA

1SNA166878R0600

1

170

CPDE-2

1SNA166741R0400

1

100

CPT-2

CPT-4 (2) FI-2/4-DIA4

TO-S-INF-VL-12.12 1SNA166723R2200

1

200

–

PO-DS-VL

1SNA166757R0400

1

117

CPP-2

Cover + –codingincluded–
FI-2/4-DIA4

Ring-tongue
Grey
TO-D-VA

1SNA166744R0700

1

139

CPT-2

–

FI-2/4-DIA4

Blue

PO-D-VA

1SNA166760R1300

1

170

CPP-2

OrangeDEO-D-VA

1SNA166874R2200

1140

CPDE-2

COR-T-R5-2.2 COR-T-4-4(1)
COR-P-R1-8.8 –(1)
FIDE-2/4 (3)1SNA166945R2100

1

190

CPT-2

–

FIT-2/4-I

FIT-2/4-I (3)

Color

Type

Part Number

Cover

Universal
plug

Pre-wired plugs

FI-2/4-DIA4

COR-T-R5-2.2 COR-T-4-4(1)
FIT-2/4-2 (3)2x4 poles

4 poles

Flush mounting
Ring-tongue
Grey
TO-E-VA–

COR-P-R1-8.8 –(1)
FIDE-2/4 (3)Base / Half-base mounting
Screw clamp
Grey
TO-DS-VLBlue

COR-T-R5-2.2 COR-T-4-4(1)
FIT-2/4-2 (3)–COR-P-R1-8.8(1)Reverse mounting
Ring-tongue
Grey
TO-I-VA-2(1) Compatible with some restrictions.
(2) Compatible in base mounting only.
(3) Plug to be mounted / see customized plugs page.
Information on pre-wired plugs: Please refer to page "ESSAILEC® pre-wired plugs for voltage transformers".

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS–

1SNC169021S0201

4

G32, TH 35-7.5,
TH 35-15

Voltage transformers application
ESSAILEC® sockets for voltage transformers - Break before makeAccessories

4

5

2

6

3

7

1
2
3
4
6
7
5

Description

TypePart Number

Interlocking peg
Mounting kits

CVABM
KEM-3
FX
KEM-1
PCVA
PCVL
BJ-VL

1SNA183436R0500
1SNA166962R0000
1SNA167682R2300
1SNA166928R2000
1SNA167496R1100
1SNA167681R2200
1SNA167680R0500

For 2 sockets assembly
For TH35 rail (a)For DIN 1 rail (a)For ring-tongue flush mounting (b)Lateral jumper bars Compatible with ring-tongue connection only (VA) (b)Compatible with screw connection only (VL); IP20 (c)Jumper bars
For two sockets screw connection type (c)

Pkg
qty
10
10
10
50
10
10
10

Weight1 pce g
0.4
24
20
18
1
1
1

(a) compatible with base mounting only.
(b) compatible with ring-tongue connection type socket only (VA).
(c) compatible with screw connection type socket only (VL).

Compatible products

Lid
CPC-1

Cover
CPC-7

4

Universal plugFI-2/4-DIA4

Plug 2x4 poles
COR-T-R5-2.2

Plug 4 poles
COR-T-4-4
Design for insertion 01-02-03-04

Connection technologies

Ring-tongue

Screw clamp

1SNC169021S0201

1

PAGE 41Voltage transformers application
Closed contact test principle - Measurement with 4 poles test plug

FIT-1/4-D
Customized plug to be
wired by user.

Test equipment

01
02
03
04

01
02
03

L1

L2

L3

04

1

01

2

02

3

03

4

04

Equipment

N

1SNC169008S0201

4

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS4

PAGE 43

Voltage transformers application
Closed contact test principle - With 4 poles test plug
Applications• Measurement on VT's

1. Normal service

1

1.1 ESSAILEC® voltage sockets
allow the simultaneous testing operations of 1 to 4 independent circuits on the same socket.

1.2 The lid is installed on the socket and canbe sealed to prevent unauthorized access.
The socket has no mobile contacts(closed style) (1).
Circuit continuity is permanent,
no possibility of disconnection.

4

1

Normalservice

4. Back to normal service

4

Back tonormalservice

4.1 The plug is removed, and lid is put back in place,signals never stop to flow through the socket.

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

4.2 The lid is put back in place.

2. Preparation: plug and lid

2.1 The lid is removed.

2.2 Connect the ESSAILEC® test
plug leads to the test set.

42

Preparation

3. Test phase: Make & Measure

3

Test phase:
Make
COR-T-4-4
Design for insertion 01-02-03-04

1SNC169015S0201

The plug is fully inserted in the socket, the signals are derived into the plug towards the test set.

PAGE 45

Voltage transformers application
ESSAILEC® sockets for voltage transformers – closed contact
Description
Closed contact principle:• The electrical connection is continuous. The circuit still closed during the testing operation.
• Closed contacts for measurement and distribution applications.
• By convention, grey coding is for voltage circuits blue coding is for polarity circuits and orange coding is fortrip circuits.
1SNC169297V0014

x4

TF-E-VA

Main technical data

Mounting instructions

Connecting capacity
Rigid: Solid/Stranded
Flexible with insulated ferrule
Flexible with insulated ferruleØ lug hole size
Width

Screw clamp(VL)
Ring tongue
(VA)

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range
Protection without lid / with lid
Coding color

IEC 947-1Rail

0.2 ... 6 mm²0.22 ... 4 mm²0.34 ... 10 mm²
3 mm
7.5 mmPolycarbonate
Silver-plated
400 V
4000 V
3
8A
25 A/5 s ... 800 A/25 ms-25 ... +70 °C-10 ... +55 °C
IP20 / IP40
Grey
- Blue- Orange

Screw clamp

Ordering details
Color

Wire
strippinglength

9.5 mm0.370 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 ... 0.8 Nm
4.4 ... 7.1 lb.in

Compatible products
Part Number

Pkg Weight
qty 1 pce g

Lid

Cover

1
1

170
170

CPT-1
CPP-1

–

Universal
plug

Pre-wired plugs
2x4 poles

4 poles––

COR-T-4-4
FIP-1/4-D (1)FIP-1/4-G (1)Flush mounting
Ring-tongue
Grey
TF-E-VABlue
PF-E-VA

1SNA166745R0000
1SNA166761R0000

Base / Half-base mounting
Screw clamp
Grey
TF-DS-VLBlue
PF-DS-VL

1SNA166503R2700
1SNA166506R2200

1
1

120
117

CPT-1
CPP-1

CPT-5 (2) –––COR-T-4-4
FIP-1/4-D (1)FIP-1/4-G (1)Ring-tongue
Grey
TF-D-VABlue
PF-D-VA
DEF-D-VA
Orange1SNA166746R0100
1SNA166762R0100
1SNA166896R1100

1
1
1

119
140
140

CPT-1
CPP-1
CPDE-1––

COR-T-4-4
FIP-1/4-D (1)FIP-1/4-G (1)–(1) Plug to be mounted / see customized plugs page.
(2) Compatible in base mounting only.
Information on pre-wired plugs: Please refer to page "ESSAILEC® pre-wired plugs for voltage transformers".

1SNC169023S0201

4

Type

G32, TH 35-7.5,
TH 35-15

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Voltage transformers application
ESSAILEC® sockets for voltage transformers – closed contact
Accessories

4

5

2

6

3

7

1
2
3
4
6
7
5

Description

TypePart Number

Interlocking peg
Mounting kits

CVABM
KEM-3
FX
KEM-1
PCVA
PCVL
BJ-VL

1SNA183436R0500
1SNA166962R0000
1SNA167682R2300
1SNA166928R2000
1SNA167496R1100
1SNA167681R2200
1SNA167680R0500

For 2 sockets assembly
For TH35 rail (a)For DIN 1 rail (a)For ring-tongue flush mounting (b)Lateral jumper bars Compatible with ring-tongue connection only (VA) (b)Compatible with screw connection only (VL); IP20 (c)Jumper bars
For two sockets screw connection type (c)

Pkg
qty
10
10
10
50
10
10
10

Weight1 pce g
0.4
24
20
18
1
1
1

(a) compatible with base mounting only.
(b) compatible with ring-tongue connection type socket only (VA).
(c) compatible with screw connection type socket only (VL).

Compatible products

Lid
CPC-1

Cover
CPC-7

4

Plug 4 poles
COR-T-4-4
Design for insertion 01-02-03-04

Connection technologies

Ring-tongue

Screw clamp

1SNC169023S0201

1

PAGE 47

Voltage transformers application
ESSAILEC® sockets for voltage transformers – independent circuits
Description
Four independent circuits for voltage measurement.

x4

1SNC169294V0014

Test directly performed on the four built-in dia. 4mm test sockets (no plug required).
Test sockets color coding :• U1- brown,• U2-black,• U3-red,• U4-blue.
The socket is supplied with a compact cover and sealing option (no coding required).

Main technical data

Mounting instructions

Connecting capacity

Rail

IEC 947-1

Rigid: Solid/Stranded
0.2 ... 6 mm²
Flexible with insulated ferrule
0.22 ... 4 mm²
Flexible with non insulated ferrule 0.22 ... 4 mm²
Body
Polycarbonate
Conductive parts
Silver-plated
Rated voltage
400 V
Impulse withstand voltage
4000 V
Pollution degree
3
Rated current
8A
Short-circuit current
25 A/5 s ... 800 A/25 ms
Storage temperature range-25 ... +70 °C
Working temperature range
10 ... +55 °C
Protection without cover/ lid
IP20

Wire stripping
lengthOrdering details

Compatible products

Screw clamp(VL)

TT4-S-VL-INF

Color
4

TH 35-7.5,
TH 35-15
9.5 mm0.370 in

TypePart Number

Tool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 ... 0.8 Nm
4.4 ... 7.1 lb.in

Pkg Weight
qty 1 pce g

Lid / Cover

Cover

40

IncludedincludedBase / Half-base mounting
Grey

TT4-S-VL-INF

1SNA166972R0000

114

Information on pre-wired plugs: Please refer to page "ESSAILEC® pre-wired plugs for voltage transformers".

Accessories
1

4

7

2

5

3

6

1
2
3
4
5
6
7

Description

TypePart Number

Interlocking peg
Mounting kits

CVABM
KEM-3
FX
KEM-1
BJ-VL
PCVA
PCVL

1SNA183436R0500
1SNA166962R0000
1SNA167682R2300
1SNA166928R2000
1SNA167680R0500
1SNA167496R1100
1SNA167681R2200

For 2 sockets assembly
For TH35 rail (a)For DIN 1 rail (a)For ring-tongue flush mounting (b)Jumper bars
For two sockets screw connection type (c)Lateral jumper bars Compatible with ring-tongue connection only (VA) (b)Compatible with screw connection only (VL); IP20 (c)

Pkg
qty
10
10
10
50
10
10
10

Weight1 pce g
0.4
24
20
18
1
1
1

(a) compatible with base mounting only.
(b) compatible with ring-tongue connection type socket only (VA).
(c) compatible with screw connection type socket only (VL).

Side view right
1SNC169024S0201

Side view left

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Voltage transformers application
ESSAILEC® pre-wired plugs for voltage transformers
Description• Standard voltage plugs are compatible with ESSAILEC® voltage sockets.
• Plugs are ready to use with contact pins (BRE...) , coding, cables and test plugs assembled to ease yourtest operations.

Main technical data
Connecting capacity

IEC 947-1

Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range

Polycarbonate
Silver-plated
400 V
4000 V
3
15 A
25 A/5 s ... 800 A/25 ms-25 ... +70 °C-10 ... +55 °C

Compatible
products

Ordering details
Description

TypePart Number

Pkg Weight
qty 1 pce g

SocketFI-2/4-DIA4

1SNA167936R1100

1

TC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VADEO-E- A
DEO-D-VA

Universal plugs
62

4

Continue on next page

1SNC169025S0201

Plug 2x4 pins,with direct insertion Ø 4 mm test plug

PAGE 49

Voltage transformers application
ESSAILEC® pre-wired plugs for voltage transformers
Compatible
products

Ordering details
Description

TypePart Number

Pkg Weight
qty 1 pce g

Socket1 plug 2x4 pins PRECODED 2.2 / Grey
4 x Ø 4 mm test plugs / Black4 x Ø 4 mm test plugs / Red
Conductors section: 2.5 mm²
cable length: 2 m / 79"

COR-T-R5-2.2

1SNA167933R1600

1

1070

1 plug 2x4 pins PRECODED 8.8 / Blue4 x Ø 4 mm test plugs / Black4 x Ø 4 mm test plugs / Red
Conductors section: 2.5 mm²
cable length: 2 m / 79"

COR-P-R1-8.8

1SNA166978R0000

1

1080

TC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VA

COR-T-4-4

1SNA167935R1000

1500

Plug 2x4 poles

Plug 4 poles
1 plug 4 pins / Grey
Design for insertion 01-02-03-04 (D.
design.)4 x Ø 4 mm test plugs / Black
Conductors section: 2.5 mm²
cable length: 2 m / 79"

TC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
TF-E-VA
TF-DS-VL
TF-D-VA

1SNC169025S0201

4

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Voltage transformers application
ESSAILEC® customized plugs
Description
To create a customized ESSAILEC® plug, according to the current socket chosen:• Select a plug,• Add contact pins (BRE...) and coding pins (COP...) if necessary,• Choose the test plugs required by the measurement tool.

Ordering details
Description

Color

Type

Part Number

Pkg Weight
qty 1 pce g

Compatible
products
Socket1 pole plug with contact pins
Plug 2 poles with 2.5 mm²contact pins (BRE-T-2.5),
without coding pins

Grey
Red

FIT-2/1-1
FIT-2/1-2

1SNA166821R1500
1SNA166644R0300

1
1

30
30

TC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
TO-I-VA-2
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VADEO-E- A
4

Plugs without contact pins (contact pins BRE..., to be ordered separately)

Plug 2 poles with 2.5 mm²contact pins
(BRE-T-2.5), without coding
pins

Grey

FIT-2/4-2

1SNA166937R1100

1

105

Blue

FIP-2/4-2

1SNA166939R2300

1

105

Orange

FIDE-2/4-2

1SNA166943R2700

1

105

TC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VADEO-E- A
DEO-D-VA

Continue on next page

1SNC169026S0201

2x4 poles
Plugs 2x4 poles, long cover,with 2 coding
pins (COP-FI-1) and 8 locking
pin.
Contacts pins (BRE-T...) to beorderedseparately.

PAGE 51

Voltage transformers application
ESSAILEC® customized plugs
Ordering details
Description

Color

Type

Part Number

Pkg Weight
qty 1 pce g

Plugs 2x4 poles, short cover,with 2 coding
pins (COP-FI-1) and 8 locking
pins.
Contacts pins (BRE-T...) to beorderedseparately.

Grey

FIT-2/4-1

1SNA166550R0100

1

91

Blue

FIP-2/4-1

1SNA166559R0600

1

91

Orange

FIDE-2/4

1SNA166877R2500

1

91

Grey

FIT-2/4-I

1SNA166672R0700

1

60

Grey

FIT-1/4-G

1SNA166547R2200

1

60

Blue

FIP-1/4-G

1SNA166556R2300

1

60

Orange

FIDE-1/4-G

1SNA166898R2300

140Plug 4 poles - insertion 01-0203-04, with
1 coding pin (COP-FI-1) and 4
locking pins.
Contacts pins (BRE-T...) to beorderedseparately.
4 PolesPlug 4 poles - insertion 1-2-34, with 1
coding pin (COP-FI-1) and 4
locking pins.
Contacts pins (BRE-T...) to beorderedseparately.

SocketTC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VADEO-E- A
DEO-D-VA
TO-I-VA-2

TC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
TF-E-VA
TF-DS-VL
TF-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VA
PF-E-VA
PF-DS-VL
PF-D-VA
DEO-D-VA
DEF-D-VA
DEO-E-VA
Continue on next page

1SNC169026S0201

4

Compatible
products

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

Voltage transformers application
ESSAILEC® customized plugs

Description

Color

Type

Part Number

Pkg Weight
qty 1 pce g

Plug 4 poles - insertion 01-0203-04, with
1 coding pin (COP-FI-1) and 4
locking pins.
Contacts pins (BRE-T...) to beorderedseparately.

Grey

FIT-1/4-D

1SNA166546R2100

1

60

Blue

FIP-1/4-D

1SNA166555R2200

160

Orange

FIDE-1/4-D

1SNA166897R1200

1

40

Compatible
products
SocketTC-E-VA
TC-E-VA-2.2
TC-E-VA-R2-2.2
TC-DS-VL
TC-S-INF-VL-2.2
TC-D-VA
TC-TH35-VL
TC-E-C5A-2.2
TO-E-VA
TO-E-VA-12.12
TO-DS-VL
TO-S-INF-VL-12.12
TO-D-VA
TF-E-VA
TF-DS-VL
TF-D-VA
PC-E-VA
PC-E-VA-8.8
PC-DS-VL
PC-D-VA
PO-E-VA
PO-DS-VL
PO-D-VA
PF-E-VA
PF-DS-VL
PF-D-VA
DEO-D-VA
DEF-D-VA
DEO-E-VA
4

1SNC169026S0201

Ordering details

PAGE 53Voltage transformers application
ESSAILEC® customized plugs
Compatible
products

Accessories
Description

1

BRE contact pins
Pin 0.34 mm²
Pin 0.75 mm²
Pin 1 mm²
Pin 1.5 mm²
Pin 2.5 mm²
Pin 4 mm²
Pin 6 mm²
Tools for contact pins
1 Pin extraction tool
2 Crimping tool for BRE pins 1 to 2.5 mm² (1)3 Locking sleeve for contact pin

2

Type

Part Number

Pkg Weight
qty 1 pce g

Socket

BRE-T-0.34
BRE-T-0.75
BRE-T-1
BRE-T-1.5
BRE-T-2.5
BRE-T-4
BRE-T-6

1SNA168160R1400
1SNA167779R1300
1SNA164921R1700
1SNA164922R1000
1SNA164923R1100
1SNA166980R0000
1SNA168147R0300

50
50
50
50
50
100
50

2
2.9
3
2.6
2
3
3

–
–
–
–
–
–
–

EXBR1
PSC
DLVR

1SNA167008R0300
1SNA173181R1300
1SNA167971R2400

1
1
10

24
478
0.4

–
–
–

FC4-1
FC4-5

1SNA167927R1000
1SNA167931R1400

10
10

11
10

–
–

COP-FI-1

1SNA167378R1100

10

2.3

–

Dia 4 mm test plugs
4
5

3
4

IP20 with mobile protection
IP20 with permanent protection

Coding pins

5

6

Plug coding pin(1) Refering to 1SNC169040D1702 to find other crimping tools

6

4

Pin installation on plugs

Locking pin, DLVR supplied withthe plug

1SNC169026S0201

BRE pin

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKSFor all applications
ESSAILEC® protection lids and covers
Description
During normal operation, lids and covers ensure protection of the test sockets from dust and unauthorizeduse.
According to the mounting choice, two options available:• a lid for all types of mounting• a cover required for base mounting ("S/DS" mounting coding)In the case of opened contacts sockets, electrical continuity covers or lids are required. The electrical continuity is provided thanks to inner pins and linking bar.

Main technical data
Protection with cover / lid

IP40

Ordering details
Description

Color

Type

Part Number

Pkg Weight
qty 1 pce g

Green
Grey
Blue
Orange
Grey

CPC-1
CPT-1
CPP-1
CPDE-1
CPT-RJ45

1SNA166578R0100
1SNA166646R0500
1SNA166647R0600
1SNA166876R2400
1SNA167002R0000

1
1
1
1
1

30
30
30
30
25.4

Grey
Blue
OrangeCPT-2
CPP-2
CPDE-2

1SNA166577R2000
1SNA166645R0400
1SNA166926R1600

1
1
1

40
40
40

Green
Grey

CPC-7 (1)CPT-5

1SNA166734R2500
1SNA166930R2600

1
1

66
66

Grey

CPT-4

1SNA166733R2400

1

78

Lid
Protecting lid for current sockets
Protecting lid for voltage sockets
Protecting lid for trip sockets
Protecting lid for polarity sockets
Lid for RJ45 socket (spare part)

Lid with electrical continuity
Protecting lid for voltage sockets
Protecting lid for polarity sockets
Protecting lid for trip sockets

CoverProtecting cover for current sockets
Protecting cover for voltage sockets

Cover with electrical continuity
Protecting cover for voltage sockets(1) CPC-7 is compatible with CC-S-INF-VL-6.6 sockets.

1SNC169027S0201

5

PAGE 55ESSAILEC® multicircuits
Range 10, 20 points
Description

1SNC169118V0014• Designed for high density wiring inside panels.
• Alternative to large terminal strips.
• Allows easy circuits disconnection without wiring modification.
Multi-circuit blocks can be mounted side by side for compact panel board wiring in replacement of large
terminal strip.

Main technical data

M10-D-C5A

Mounting instructions

Connecting capacity

IEC 947-1

Socket

0.5 ... 0.8 Nm
2.5 mm²
Pin BRE
Polycarbonate
Silver-plated
400 V
4000 V
3
8A
25 A/5 s ... 800 A/25 ms-25 ... +70 °C-10 ... +55 °C
IP20 / IP40

Quick connect (C5A)
Flexible with insulated ferrule

Plug
Body
Conductive parts
Rated voltage
Impulse withstand voltage
Pollution degree
Rated current
Short-circuit current
Storage temperature range
Working temperature range
Protection without cover/ lid

Ordering details

Wire stripping
length

9.5 mm0.370 inCompatible products
Part Number

Pkg Weight
qty 1 pce g

Plug

SocketHalf-base mounting
Grey
M10-D-C5A

1SNA166513R1000

10

60

FIM10-1–

Extension mounting
Grey
M10-P-C5A

1SNA166772R0300

10

66

–

–

Rack mounting
Grey
M10-R-C5A

1SNA166566R2500

10

60

FIM10-R–

Reverse mounting
Grey
M10-I-C5A-1
M20-I-C5A

1SNA166774R0500
1SNA166777R0000

10
1

100
190

FIM10-I-1
FIM20-I––

1SNA166516R1300
1SNA166573R2400
1SNA166574R2500
1SNA166576R2700

10
1
1
1

55
54
30
53

–
–
–
–

M10-D-C5A
M10-R-C5A
M10-I-C5A-1
M20-I-C5A

Color

Type

Sockets

M10-D-C5A

M20-I-C5A

Plugs
Grey
FIM10-1

6

FIM10-1
FIM10-R
FIM10-I-1
FIM20-I

The various accessories necessary for each mounting option are supplied with the socket as well as the 2 coding pins COP-E-1 (see coding section).
The BRT contacts pins are to be ordered separately.

FIM20-I

Description

1

2

3

4

For sockets
1 For 2 sockets assembly
For plugs
2 Pin 0.34 mm²
Pin 0.75 mm²
Pin 1 mm²
Pin 1.5 mm²
Pin 2.5 mm²
Pin 6 mm²
3 Pin extraction tool
4 Crimping tool for BRE pins 1 to 2.5 mm² (1)(1) Refering to 1SNC169040D1702 to find other crimping tools

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

TypePart Number

Pkg Weight
qty 1 pce g

CVABM

1SNA183436R0500

10

0.4

BRE-T-0.34
BRE-T-0.75
BRE-T-1
BRE-T-1.5
BRE-T-2.5
BRE-T-6
EXBR1
PSC

1SNA168160R1400
1SNA167779R1300
1SNA164921R1700
1SNA164922R1000
1SNA164923R1100
1SNA168147R0300
1SNA167008R0300
1SNA173181R1300

50
50
50
50
50
50
1
1

2
2.9
3
2.6
2
3
24
478

1SNC169028S0201

Accessories

Mounting instructions

Mounting instructions for coding

58

Outer dimensions, mounting instructions

60

Summary_5

7

PAGE 57

ESSAILEC®
Mounting instructions for coding
Socket coding pin

Plug coding pin

Plug coding pin

Coding pins
symbolSocket coding pin

Socket coding

2

4

6

8

10

12

4

6

8

10

12

Plug coding

COP-E-1

COP-FI-1

2

These numbers correspond to the coding information
For instance:
CC-E-VA-6.6 corresponds to COR-C-R4-6.6
TC-E-VA-2.2 corresponds to COR-T-R5-2.2

Ordering details
Description

TypePart Number

Pkg

Weightqty

kg

Socket coding pin

COP-E-1

1SNA167379R1200

10

2.3

Plug coding pin

COP-FI-1

1SNA167378R1100

10

2.3

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169029S0201

7

ESSAILEC®
Mounting instructions for coding

How to insert the coding pins?

Step 1 - Socket
Choose a coding code for the socket. Then, insert the coding pin(COP-E-1) from below into the socket.

Step 2 - PlugIn order to guarantee a perfect compatibility between thesocket coding and the plug coding, you have to:
1. Insert the coding pin for the plug (COP-FI-1) inside the socket.

7

1SNC169030S0201

2. On a second time, connect the plug on the socket to insert the plug
coding within the plug.

PAGE 59ESSAILEC®
Outer dimensions
Sockets
40

80.2

63

40

44

Half-base mounting

Rack mounting

44

1

47.

Base mounting with KEM-3

43.

7

80.2

66.7

74

63

3

Base mounting

.5

49

50

5
51.
59
TH35 rail mounting

Lids and covers

Lid

Cover

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169022S0201

7

RJ45

ESSAILEC®
Outer dimensions
Plugs

Plug 2x4 poles short cover

Reverse mounting

7

1SNC169022S0201

Plug 2x4 poles long cover

PAGE 61ESSAILEC®
Outer dimensions, mounting instructions
Sockets

35
=

=

56.5

73

±0.1

2 x M34 x M4Ø 3.1

Base mounting
0.5 Nm < Tightening torque< 0.8 Nm.

Flush mounting

Base mounting

Flush mounting
The flush mounting kit must be mounted on thesocket prior to the installation on the panel.
Tightening torque = 0.5 Nm maxi.

44

89

.5

Half-base mounting - Rack mounting
The rack mounting is suppliedwith 2 additional guiding pins.
0.5 Nm < Tightening torque < 0.8 Nm.

Reverse mounting

Lids and covers

Flush mounting

Base mounting

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

1SNC169022S0201

7

Flush mounting (RJ45)ESSAILEC® multicircuits
Outer dimensions, mounting instructions

13

M20-I-C5A
20 points multicircuits half-base reverse
mounting socket

M20-C5A
20 points multicircuits
half-base mounting socket

75

22

22

27

M10-I-C5A-1
10 points multicicuits
half-base reverse mounting
socket

M10-D-C5A
10 points multicircuits
half-base mounting
socket

63

27

63

76

63

63

63

Outer dimensions
Sockets

13

63

Plugs

12

76

13

22 2 131

FIM20
20 points multicircuits
half-base mounting plug

FIM20-I
20 points multicircuits
half-base reverse mounting
plug

FIM10-I-1
10 points multicicuits
half-base reverse
mounting plug

22

75

FIM10-1
10 points multicircuits
half-base mounting
plug

Mounting instructions

4 x Ø 2.5
20 points multicircuits
half-base mounting socket

2 x Ø 2.5

2 x Ø 2.5

10 points multicicuits
half-base reverse mounting
plug

10 points multicircuits
half-base mounting socket

PAGE 63

1SNC169022S0201

4 x Ø 2.5
20 points multicircuits
half-base reverse mounting
plug

22
==

22
==

=

50
56.5

22

50
56.5

=
=

50
56.5

22

50
56.5

=

7

IndexPart Number classification
Part Number
1SNA164921R1700
1SNA164922R1000
1SNA164923R1100
1SNA166503R2700
1SNA166506R2200
1SNA166513R1000
1SNA166516R1300
1SNA166523R1200
1SNA166525R1400
1SNA166529R2000
1SNA166546R2100
1SNA166547R2200
1SNA166550R0100
1SNA166555R2200
1SNA166556R2300
1SNA166559R0600
1SNA166566R2500
1SNA166573R2400
1SNA166574R2500
1SNA166576R2700
1SNA166577R2000
1SNA166578R0100
1SNA166589R2500
1SNA166625R2000
1SNA166627R2200
1SNA166628R0300
1SNA166630R0100
1SNA166638R0500
1SNA166643R0200
1SNA166644R0300
1SNA166645R0400
1SNA166646R0500
1SNA166647R0600
1SNA166672R0700
1SNA166722R2100
1SNA166723R2200
1SNA166733R2400
1SNA166734R2500
1SNA166737R2000
1SNA166738R0100
1SNA166741R0400
1SNA166742R0500
1SNA166743R0600
1SNA166744R0700
1SNA166745R0000
1SNA166746R0100
1SNA166747R0200
1SNA166748R1300
1SNA166757R0400
1SNA166758R1500

Type
Page
BRE-T-1
54
BRE-T-1.5
54
BRE-T-2.5
54
TF-DS-VL
46
PF-DS-VL
46
M10-D-C5A
56
FIM10-1
56
CC-R-VA
22
FIC-2/4-1
26
FIC-2/4-R
26
FIT-1/4-D
53
FIT-1/4-G
52
FIT-2/4-1
52
FIP-1/4-D
53
FIP-1/4-G
52
FIP-2/4-1
52
M10-R-C5A
56
FIM10-R
56
FIM10-I-1
56
FIM20-I
56
CPT-2
55
CPC-1
55
FIC-2/4-I
26
CC-E-VA-6.6
22
TC-E-VA-2-2
34
TC-E-C5A-2.2
34
PC-E-VA-8.8
34
COR-C-R1-6.6
24
COR-C-3
24
FIT-2/1-2
51
CPP-2
55
CPT-1
55
CPP-1
55
FIT-2/4-I
52
CC-S-INF-VL-6.6
22
TO-S-INF-VL-12.12
40
CPT-4
55
CPC-7 (1)55
CC-E-VA
22
CC-D-VA
22
TO-DS-VL
40
TC-DS-VL
34
TO-E-VA40
TO-D-VA40
TF-E-VA
46
TF-D-VA
46
TC-E-VA
34
TC-D-VA34
PO-DS-VL
40
PC-DS-VL
34

Part Number
1SNA166759R1600
1SNA166760R1300
1SNA166761R0000
1SNA166762R0100
1SNA166763R0200
1SNA166764R0300
1SNA166772R0300
1SNA166774R0500
1SNA166777R0000
1SNA166778R1100
1SNA166819R2300
1SNA166821R1500
1SNA166874R2200
1SNA166876R2400
1SNA166877R2500
1SNA166878R0600
1SNA166896R1100
1SNA166897R1200
1SNA166898R2300
1SNA166925R1500
1SNA166926R1600
1SNA166928R2000
1SNA166930R2600
1SNA166936R1000
1SNA166937R1100
1SNA166939R2300
1SNA166941R2500
1SNA166943R2700
1SNA166945R2100
1SNA166948R0400
1SNA166962R0000
1SNA166963R0000
1SNA166964R0000
1SNA166972R0000
1SNA166976R0000
1SNA166977R0000
1SNA166978R0000
1SNA166979R0000
1SNA166980R0000
1SNA167002R0000
1SNA167008R0300
1SNA167260R1700
1SNA167264R0700
1SNA167265R0000
1SNA167378R1100
1SNA167379R1200
1SNA167496R1100
1SNA167622R2600
1SNA167623R2700
1SNA167624R2000

Type
PO-E-VA
PO-D-VA
PF-E-VA
PF-D-VA
PC-E-VA
PC-D-VA
M10-P-C5A
M10-I-C5A-1
M20-I-C5A
COR-C-R2-6.6
FIC-2/1-1
FIT-2/1-1
DEO-D-VA
CPDE-1
FIDE-2/4
DEO-E-VA
DEF-D-VA
FIDE-1/4-D
FIDE-1/4-G
TO-E-VA-12.12
CPDE-2
KEM-1
CPT-5
FIC-2/4-2
FIT-2/4-2
FIP-2/4-2
CC-I-VA-2
FIDE-2/4-2
TO-I-VA-2
TC-S-INF-VL-2.2
KEM-3
CC-TH35-VL-6.6
TC-TH35-VL
TT4-S-VL-INF
CC-E-VA-R2-6.6
TC-E-VA-R2-2.2
COR-P-R1-8.8
COR-C-R3
BRE-T-4
CPT-RJ45
EXBR1
BRE-C-2.5
BRE-C-1
BRE-C-1.5
COP-FI-1
COP-E-1
PCVA
IR1
IR2
IR3

Page
40
40
46
46
34
34
56
56
56
24
26
51
40
55
52
40
46
53
52
40
55
23
55
26
51
51
22
51
40
34
23
22
34
48
22
34
50
24
54
14
26
26
26
26
58
58
23
26
26
26

Part Number
1SNA167680R0500
1SNA167681R2200
1SNA167682R2300
1SNA167690R0700
1SNA167692R2500
1SNA167697R2200
1SNA167779R1300
1SNA167927R1000
1SNA167931R1400
1SNA167932R1500
1SNA167933R1600
1SNA167934R1700
1SNA167935R1000
1SNA167936R1100
1SNA167937R0000
1SNA167971R2400
1SNA167981R1700
1SNA168146R0200
1SNA168147R0300
1SNA168160R1400
1SNA173181R1300
1SNA183436R0500
1SNA205876R0400
1SNA566000R0000
1SNA566001R0000

Type
BJ-VL
PCVL
FX
FCB-1
FCB-2
CA
BRE-T-0.75
FC4-1
FC4-5
COR-C-R4-6.6
COR-T-R5-2.2
COR-C-R5-6.6
COR-T-4-4
FI-2/4-DIA4
FIC-2/4-DIA4
DLVR
DI
BRE-C-6
BRE-T-6
BRE-T-0.34
PSC
CVABM
BRE-C-4
TC-E-RJ45-INF
FI-RJ45-DIA4

Page
23
23
23
26
26
26
54
26
26
24
50
24
50
49
25
26
26
26
54
54
26
23
26
14
14

Index

8

INDUSTRIAL /// ENTRELEC - ESSAILEC® TEST BLOCKS

IndexType classification
Part Number
Page
1SNA167680R0500
23
1SNA167264R0700
26
1SNA167265R0000
26
1SNA167260R1700
26
1SNA205876R0400
26
1SNA168146R0200
26
1SNA168160R1400
54
1SNA167779R1300
54
1SNA164921R1700
54
1SNA164922R1000
54
1SNA164923R1100
54
1SNA166980R0000
54
1SNA168147R0300
54
1SNA167697R2200
26
1SNA166738R0100
22
1SNA166737R2000
22
1SNA166625R2000
22
1SNA166976R0000
22
1SNA166941R2500
22
1SNA166523R1200
22
1SNA166722R2100
22
1SNA166963R0000
22
1SNA167379R1200
58
1SNA167378R1100
58
1SNA166643R0200
24
1SNA166638R0500
24
1SNA166778R1100
24
1SNA166979R0000
24
1SNA167932R1500
24
1SNA167934R1700
24
1SNA166978R0000
50
1SNA167935R1000
50
1SNA167933R160050
1SNA166578R0100
55
1SNA166734R2500
55
1SNA166876R2400
55
1SNA166926R1600
55
1SNA166647R0600
55
1SNA166645R0400
55
1SNA166646R0500
55
1SNA166577R2000
55
1SNA166733R2400
55
1SNA166930R2600
55
1SNA167002R0000
14
1SNA183436R0500
23
1SNA166896R1100
46
1SNA166874R2200
40
1SNA166878R0600
40
1SNA167981R1700
26
1SNA167971R2400
26

Type
EXBR1
FC4-1
FC4-5
FCB-1
FCB-2
FI-2/4-DIA4
FIC-2/1-1
FIC-2/4-1
FIC-2/4-2
FIC-2/4-DIA4
FIC-2/4-I
FIC-2/4-R
FIDE-1/4-D
FIDE-1/4-G
FIDE-2/4
FIDE-2/4-2
FIM10-1
FIM10-I-1
FIM10-R
FIM20-I
FIP-1/4-D
FIP-1/4-G
FIP-2/4-1
FIP-2/4-2
FI-RJ45-DIA4
FIT-1/4-D
FIT-1/4-G
FIT-2/1-1
FIT-2/1-2
FIT-2/4-1
FIT-2/4-2
FIT-2/4-I
FX
IR1
IR2
IR3
KEM-1
KEM-3
M10-D-C5A
M10-I-C5A-1
M10-P-C5A
M10-R-C5A
M20-I-C5A
PC-DS-VL
PC-D-VA
PC-E-VA
PC-E-VA-8.8
PCVA
PCVL
PF-DS-VL

Part Number
Page
1SNA167008R0300
26
1SNA167927R1000
26
1SNA167931R1400
26
1SNA167690R0700
26
1SNA167692R2500
26
1SNA167936R110049
1SNA166819R2300
26
1SNA166525R1400
26
1SNA166936R1000
26
1SNA167937R0000
25
1SNA166589R2500
26
1SNA166529R2000
26
1SNA166897R120053
1SNA166898R2300
52
1SNA166877R2500
52
1SNA166943R2700
51
1SNA166516R1300
56
1SNA166574R2500
56
1SNA166573R2400
56
1SNA166576R2700
56
1SNA166555R2200
53
1SNA166556R2300
52
1SNA166559R0600
52
1SNA166939R2300
51
1SNA566001R0000
14
1SNA166546R2100
53
1SNA166547R2200
52
1SNA166821R1500
51
1SNA166644R0300
51
1SNA166550R0100
52
1SNA166937R1100
51
1SNA166672R0700
52
1SNA167682R2300
23
1SNA167622R2600
26
1SNA167623R2700
26
1SNA167624R2000
26
1SNA166928R2000
23
1SNA166962R0000
23
1SNA166513R1000
56
1SNA166774R0500
56
1SNA166772R0300
56
1SNA166566R2500
56
1SNA166777R0000
56
1SNA166758R1500
34
1SNA166764R0300
34
1SNA166763R0200
34
1SNA166630R0100
34
1SNA167496R1100
23
1SNA167681R2200
23
1SNA166506R2200
46

Type
PF-D-VA
PF-E-VA
PO-DS-VL
PO-D-VA
PO-E-VA
PSC
TC-DS-VL
TC-D-VA
TC-E-C5A-2.2
TC-E-RJ45-INF
TC-E-VA
TC-E-VA-2-2
TC-E-VA-R2-2.2
TC-S-INF-VL-2.2
TC-TH35-VL
TF-DS-VL
TF-D-VA
TF-E-VA
TO-DS-VL
TO-D-VA
TO-E-VA
TO-E-VA-12.12
TO-I-VA-2
TO-S-INF-VL-12.12
TT4-S-VL-INF

Part Number
Page
1SNA166762R0100
46
1SNA166761R0000
46
1SNA166757R0400
40
1SNA166760R130040
1SNA166759R1600
40
1SNA173181R130026
1SNA166742R0500
34
1SNA166748R130034
1SNA166628R0300
34
1SNA566000R0000 14
1SNA166747R0200
34
1SNA166627R2200
34
1SNA166977R0000
34
1SNA166948R0400
34
1SNA166964R0000
34
1SNA166503R2700
46
1SNA166746R0100
46
1SNA166745R0000
46
1SNA166741R0400
40
1SNA166744R0700
40
1SNA166743R0600
40
1SNA166925R1500
40
1SNA166945R210040
1SNA166723R2200
40
1SNA166972R0000
48

8

Index

Type
BJ-VL
BRE-C-1
BRE-C-1.5
BRE-C-2.5
BRE-C-4
BRE-C-6
BRE-T-0.34
BRE-T-0.75
BRE-T-1
BRE-T-1.5
BRE-T-2.5
BRE-T-4
BRE-T-6
CA
CC-D-VA
CC-E-VA
CC-E-VA-6.6
CC-E-VA-R2-6.6
CC-I-VA-2
CC-R-VA
CC-S-INF-VL-6.6
CC-TH35-VL-6.6
COP-E-1
COP-FI-1
COR-C-3
COR-C-R1-6.6
COR-C-R2-6.6
COR-C-R3
COR-C-R4-6.6
COR-C-R5-6.6
COR-P-R1-8.8
COR-T-4-4
COR-T-R5-2.2
CPC-1
CPC-7
CPDE-1
CPDE-2
CPP-1
CPP-2
CPT-1
CPT-2
CPT-4
CPT-5
CPT-RJ45
CVABM
DEF-D-VA
DEO-D-VA
DEO-E-VA
DI
DLVR

PAGE 65

RAILWAYAPPLICATIONS
Terminal Blocks
ENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSSummary_1

As a leading supplier for railway applications,
TE Connectivity proposes the most complete
terminal block range of the market complying
with all main international railway standards.
The ENTRELEC range for railway applications isavailable in four technologies and covers all theneeds for rolling stock and railroad infrastructures.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks

Railway applications
Terminal blocks

2

1

SNK series, PI-Spring technology

112

SNK series, Pluggable technology

69

3

ADO System® IDC and Pluggable technologies

103

4

Quick-connect technology

137

5Stud technology

169

6

Screw clamp technology complying with NF F 55251 and CT448

207

7

SNK series, Screw clamp technology

219

8

Accessories

309

9

Index		

352

10

Summary_1

Ranges, solutions and standards presentation

1-1773966-1_EN - Edition January 2020

PAGE 1

ENTRELEC Terminal blocks

TE Connectivity proposes one of the largest Din Rail Terminal block offering on themarket with various technologies: screw, PI-Spring, spring, IDC, pluggable, stud, etc.
found in over 8000 products & solutions.

1

Scope

SNK
terminal blocks

Dedicated applications
terminal blocks

Terminal blocks forrailway applications

Qualified for worldwide applications andsevere environments (such as hazardous
locations, railways, marine and solar
applications..).
From 0.2 to 300 mm².

Specific terminal blocks and technologies
for dedicated applications and markets.

The largest offering on
the market for rollingstock and infrastructures.

Product
SNK PI-Springfamilies & technology
functions 2.5 to 16 mm²
12 to 4 AWG

Feed-throughMulti-deck
GroundDisconnect
for fuses
Component holder

ADO System® (IDC)
0.22 to 4 mm²
24 to 12 AWG

ADO-ADO or ADO-screw clamp SNK PI-Spring technology
Feed-through / Multi-deck /2.5 to 16 mm²Ground / Disconnect /12 to 4 AWG
for fuses / Component holder

Safety (spring loaded)
0.22 to 10 mm²
24 to 6 AWG

Feed-throughDisconnect
Test & measurement

SNK pluggablescrew & PI-Spring technologies
2.5 to 4 mm²
12 to 10 AWG

SNK screw clamp
technology
4 to 240 mm²
12 to 500 Kcmil

Feed-throughMulti-deck
GroundDisconnect
for fuses
Test & measurement
Marshalling
Component holderStud
25 to 300 mm²
4 AWG to 1000 Kcmil

One stud
2 studs
One stud - One screw clamp

ADO System® (IDC)
1.5 to 4 mm²
16 to 12 AWG

Ring lug
6 to 16 mm²
8 to 6 AWG

Feed-throughTest & measurementStud
4 to 185 mm²

SNK pluggablescrew & PI-Spring
technologies
2.5 to 4 mm²
12 to 10 AWG

Feed-throughMulti-deck
GroundMiniblocks
1.5 to 6 mm²
18 to 8 AWG

Screw clamp
SpringADO System ® (IDC)

Quick-connect
2.5 to 6 mm²

Other types
Test & measurement: with sliding link, blade, plug
Pluggable: feed-through, double deck, disconnect
Sensors/actuators: screw, spring, ADO system (IDC)
Installation: screw, spring
Protection: ground + neutral
Component holders: screw, spring, ADO system (IDC)

www.te.com

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSDBL power
distribution blocks

ESSAILEC®
test blocks

Interfast PLC
pre-wiring system

Marking
solutions

The preferred choice for primary
power distribution and solar
applications.

Test blocks for safe and easy
testing on secondary circuitsof current and voltage
transformers and sensors.

PLC pre-wiring system for fast,
flexible, reliable connection of PLC’sin process automation applications.

Markers & marking systems for
all identification requirements inelectrical panels.

From 80 A up to 550 A (IEC)

Current and voltage
sockets & plugs

Interfast PCB:
Compact & standard modules

Terminal block identification andgroup markers

Simultaneous testing of
1 to 4 independent circuitson the same socket

Interfast MS:
Modular system based onterminal block technology

Wire and cable identification

Terminal blocks types:
2 to 10 poles, up to 20 outputs

Component and equipment
identification

Several testing principle such
Functions:as “make before break” for safe – – 1 to 4 wire connections (sensors) Panel identification
current transformer testing– – Disconnect
Pre-printed markers for terminal– – Fuse
blocksPanel and switchboard
mounting : base, flush, rack,– – Signal indication
TH35 rail– – Relays
Multicircuits sockets & plugs– – Optocouplers– – Solenoid valve control– – Galvanic isolation (2.5 kV).

1SNC160261S0201

Modular blocks: single pole, three& four poles, up to 12 outputs

1

PAGE 3

ENTRELEC terminal blocks for railway applications
A recognized expertise1

TE Connectivity, a worldwide leading supplier for rolling stock and infrastructure
Compliance with main international railway standards
All technologies: PI-Spring, pluggable, ADO System® (IDC), stud and quick-connect
Customized terminal block assemblies: from design to manufacturing and packing
Easy Rail Designer 3D: ease the design of terminal blocks assemblies

Terminal blocks in infrastructure– – Electrical distribution and control panels.

PI-Spring

on
off

Screw

Pluggable

Screw
NF F 55251
and CT448

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1Terminal blocks in rolling stock– – HVAC– – Door control– – Electrical distribution– – Control system and Pilot center.

PI-Spring

Quick-connect

Pluggable

Stud

ADO

Ring lugonoff

1SNC167084S0201

System® IDC

PAGE 5

ENTRELEC terminal blocks for railway applications
Overview of ranges

SNK series, PI-Spring and pluggable technologies
The benefits of 2 technologies in 1 connection

ADO System® IDC and pluggable technologies
The fastest connection technology for rolling stock

ADO System®

Quick-connect technology
The historical technology for railway control and signal distribution

Faston1SNC167085S0201

1

Pi-Spring
Insertion
directeINDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSStud technology
The "Pull-out proof" connection for rolling stock

Vissé/ressort
1

Screw clamp technology complying with NF F 55251 and CT448
The proven reliability and performance for railway infrastructure

SNK series, Screw clamp technology

1SNC167085S0201

A smart design to support your daily connection challenges

PAGE 7

Standards and compliance

Rail vehicles are subjected to extreme environmental conditions (high vibrationand shock), corrosion (underground applications or tunnels).
All ENTRELEC terminal blocks listed in this catalog are tested in accordance with the latest
and most demanding standards applying to rolling stock applications.
1

IEC 61373 railway applications – Rolling stock equipment – Shock and vibration tests
TE Connectivity terminal blocks are complying with category 1 (body mounted) class B.
EN 45545-2 railway applications. Fire protection on railway vehicles. Requirements for fire
behavior of materials and components
TE Connectivity terminal blocks plastic materials are rated HL3 R22 (the highest Hazard
level). They can be used on vehicles for subway, tube, sleeping and couchette.
NF F 16-101 Directive relative to selecting materials in relation to their fire resistance interms of its behavior in a fire, the opacity of smoke and the toxicity of the gas released.
NF F 16-102 Complement to NF F 16-101. The purpose of this standard is to specify theapplication of NF F 16-101 to electrical equipment and especially to individual apparatus.
TE Connectivity terminal blocks plastic materials are rated I2F2. Level 3. This level concern
products mounted inside a room for passengers or running crew.
UL94 (North America) standard for safety of Flammability of Plastic Materials for parts indevices and Appliances testing
TE Connectivity terminal blocks plastic materials are rated UL94 V0.

UNI CEI 11170-3 (Italy) Fire Test to Railway Components
TE Connectivity terminal blocks have their plastic materials in accordance with the FS Italianstandard UNI EN 11170-3 according to the test conditions of ISO 11925-2 (flame 30s) and NF
F 16-101(F2 index).

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160090S0201 - Rev. A

NFPA 130 (North America) standard for Fixed Guideway Transit and Passenger rail systems
TE Connectivity terminal blocks plastic materials complies with NFPA130 per ASTM E 162
and ASTM E 662 standards tests. It also complies with FRA238.103 and BSS 7239
standards.

Railway solutions and tools
Easy Rail Designer 3D, Terminal block assembly software

Engineering, do it yourself easily
1

Customized project management– – Management of multiple projects– – Indication on the drawing of the
supplier's, integrator's and end
user's data
– – Drawing update indexing with PDF
report.

Assembling, rely on TE Connectivity expertiseTE Connectivity technical expertise–– Drawing technical verification doneby TE Connectivity experts–– 100% reliable data import to
TE Connectivity production system.

Flexible production– – 3 types of assembly:-- rail mounted-- pre-assembled-- packed in kit.
– – Possibility to add some other TE
Connectivity Din rail products.

User-friendly configurator–– Intuitive Windows® (1) user interface–– Autocorrecting system–– Powerful search engine–– Insertion of products external to the
database.
(1) Windows® is a registered trademark of Microsoft.

Optimized inventory–– Products and markers stocked by
TE Connectivity–– Marking managed by TE Connectivity–– One single product part number
corresponds to one complete
assembly.

PAGE 91SNC167101S0201

Advanced 3D drawing and data export–– Built-in 3D viewer–– Integration to CAD/CAE softwares–– Compatibility with TE Connectivity
printers–– Detailed drawings of the rail, assembly and markers.

Summary_2

2

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
PI-Spring technology
Technologies presentation		

12

Overview			

18

4 mm² / 10 AWG

6 mm² / 8 AWG
10 mm² / 6 AWG

16 mm² / 4 AWG

Ground
2.5 mm² / 12 AWG

4 mm² / 10 AWG

6 mm² / 8 AWG
10 mm² / 6 AWG
16 mm² / 4 AWG
Disconnect with blade
2.5 mm² / 12 AWG

Disconnect with plug
2.5 mm² / 12 AWG
For 5x20 fuses
2.5 mm² / 12 AWG
Double deck
2.5 mm² / 12 AWG

Triple deck
2.5 mm² / 12 AWG

Component holder
2.5 mm² / 12 AWG

ZK2.5		ZK2.5-3P
with 3 connections
ZK2.5-4P
with 4 connections
ZK4		
ZK4-3P
with 3 connections
ZK4-4P
with 4 connections
ZK6		
ZK6-3P
with 3 connections
ZK10		
ZK10-PV		
ZK10-3P
with 3 connections
ZK10-3P-PV
with 3 connections
ZK16		
ZK16-PV		ZK16-3P
with 3 connections
ZK16-3P-PV
with 3 connections

19
20
21
22
23
24
25
26
27
28
29
30
31
32
33

ZK2.5-PE		
ZK2.5-PE-3P
with 3 connections
ZP2.5-PE-4P
with 4 connections
ZK4-PE		ZK4-PE-3P
with 3 connections
ZK4-PE-4P
with 4 connections
ZK6-PE		ZK6-PE-3P
with 3 connections
ZK10-PE		
ZK10-PE-3P
with 3 connections
ZK16-PE		
ZK16-PE-3P
with 3 connections

35
36
37
38
39
40
41
42
43
44
45
46

ZK2.5-S
with test sockets
ZK2.5-S-4P
with test sockets
ZK2.5-S-R1		

47
48
49

ZK2.5-SP
ZK2.5-SP-4P

50
51

2

34

with test sockets
with test sockets

ZK2.5-SF		
ZK2.5-SF-R
with blown fuse indicator

52
53

ZK2.5-D2
ZK2.5-D1
ZK2.5-D2-PE
ZK2.5-D1-PE

2 feed-through circuits
1 feed-through circuit
1 feed-through circuit and 1 ground circuit
1 ground circuit

54
55
56
57

ZK2.5-T3
3 feed-through circuits
ZK2.5-T1
1 feed-through circuit
ZK2.5-L-L-PE		
ZK2.5-L-N-PE
2 feed-through circuits and 1 ground circuit
ZK2.5-T1-PE
1 ground circuit

58
59
60
61
62

ZK2.5-CH-4P-LR		
ZK2.5-CH-4P-RL		
ZK2.5-D-CH-UD 		
ZK2.5-D-CH-DU		
ZK2.5-D-CH2-DU-RL		

63
64

65
66
67

PAGE 11

Summary_2

Feed-through
2.5 mm² / 12 AWG

PI-Spring technology - SNK series, terminal blocks
Features and benefits

The patented PI-Spring technology provides the benefits of bothPush-In and Spring technologies in one connection

2

Speed up your projects
50% faster connection time with Push-in mode
Our Push-in connection technology allows:
A direct one step insertion with rigid and prepared flexible
conductors.
Easy and quick insertion of the prepared flexible conductor
or rigid conductor.
Reduced effort and conductor preparation time with springmode– – Our connection requires minimal effort to insert wires withthe screwdriver– – Flexible conductors preparation is not necessary.
– – The screwdriver locks onto terminal freeing up hands.

Push-in mode

Spring mode

Clear circuit identification

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK162074S0201

Better project identification– – Circuit identification is improved thanks to the 20% larger
marking area
– – Pre-mark by hand or with label on our flat marking surface
and start immediately the wiring, before the final markers
mounting– – Spare markers re-printing in case of modifications.

PI-Spring technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process
Mounting, wiring, testing… made easy
Avoid mounting and wiring errors: asymmetrical design allows
immediate visual check in case of reversed terminal blocks.

2

Asymmetrical design avoids mounting error

Faster accessories mounting
Save up to 70% mounting time thanks to :–– screwless jumpers, component plugs, test devices, end
stops and snap-in ground terminal blocks.

Screwless accessories

Snap-in ground terminal blocks

1SNK162074S0201

Closed jumper location allows great stiffness of the terminal
block, avoid deflection while tightening and optimal jumper
guiding.

Closed jumper location for stiffness.

PAGE 13

PI-Spring technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart accessories
Flexible test solutions from individual insulated test adapter totest connectors for complete assemblies testing.
–– Direct plug-in into jumpers channels–– 5, 6, 8 mm spacing, mixing various spacing is possible–– 1000 V rating.

Plug-in individual test adapter.

Plug-in test connector.

Series plug associated with disconnect blocks.

Parallel plug to be installed between 2 blocks.

Pre-cut poles easy removable byhand.

Predefined shape to identify connected poles.

2

Component holder plugs for series or parallel component
mounting (resistors, filters, diodes...).
Can be installed after wiring.
Series plug offers screwless component connection(no soldering).

1SNK162074S0201

Smart plug-in jumpers:
Pre-cut poles removable by hand: clean cut.
Insulated up to 1000 V (avoid use of separators).
Predefined shapes in molding to easily identify connected
poles with a pen.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSPI-Spring technology - SNK series, terminal blocks
Features and benefits

Optimized logistics
Reduce your accessories inventory by up to 50%
SNK PI-Spring, screw and pluggable ranges share the same
accessories.

– – All end sections and circuit separators fit several types andsizes of blocks– – One end section fits up to 21 models– – One circuit separator fits with 62 terminal blocks.

2

End sections and circuit separators fit several types and sizes of blocks

Shared accessories for SNK PI-Spring, screw and pluggable ranges

50% less inventory makes PI-Spring attractive to allworldwide markets–– The user selects one range but benefit from 2 connection
modes (push-in and spring) which have global certifications
and access to markets and applications worldwide–– Reduced packaging adapted to the usage (20 items
packaging on some items).
Push-in range + Spring range

Facilitate maintenance operations
Terminal blocks can be individually removed from a terminal
assembly equipped with markers: TE Connectivity markers
become independent after strip mounting. The markers remainon terminal in any situation.
Markers are interchangable: the smaller marker can fit
any bigger block.

PI-Spring

Reliable in harsh conditions
Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…
High corrosion resistance
PI-Spring clamp is made of high quality stainless steel.
Salt mist withstand up to 1,000 hours (as per IEC 60068).

RoHS
EAC

DNV

Rina
1SNK162074S0201

hazlocMaintenance operations facilitated

PAGE 15

SNK series, terminal blocks
PI-Spring technology - Range overview from 2.5 to 16 mm² – 12 to 4 AWG

22

3

Connections

Single deckFeed-throughGroundDisconnect
Fuse
Solar : 1500 VDC

Voltage test
screwdriver entry
point accepts
Category II probes

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSConnections

Single deckFeed-throughGroundSolar: 1500 VDC

NEW

NEW

Double central channels
allows multiconfigurations(jumpering, testing and measuring)Connections

Single deckFeed-throughGroundDisconnect
Component holder

Two circuit
separators
for the entire
range

2x 2

Connections

Double deckFeed-throughGroundComponent holder

End section
can be used
as circuit separator

3x 2

Connections

Triple deckFeed-throughGround2

Rotating label
holdereasy plug-in injumper channel

1SNK162068S0201 - Rév. A

4

PAGE 17

SNK series, terminal blocks
PI-Spring technology

Feed-throughGroundComponent holder

Section
12 AWG
10 AWG
8 AWG
6 AWG

16 mm²

4 AWG

Double deck

ZK2.5
ZK2.5-3P
ZK4
ZK4-3P
ZK6
ZK6-3P
ZK10
ZK10-3P
ZK10-PV New ZK10-3P-PV
ZK16
ZK16-3P
ZK16-PV New ZK16-3P-PV

ZK2.5-4P
ZK4-4P

Feed-through

ZK2.5-PE
ZK4-PEZK6-PE
ZK10-PE

ZK2.5-PE-3P
ZK4-PE-3P
ZK6-PE-3P
ZK10-PE-3P

ZK16-PE

ZK16-PE-3P

ZK2.5-PE 4P
ZK4-PE- 4P

Ground

ZK2.5-CH-4P-LR ZK2.5-CH-4P-RL

Component holder

Section
2.5 mm²

12 AWG

ZK2.5-D2

Triple deck

ZK2.5-D1

ZK2.5-D2-PE

ZK2.5-D1-PE

ZK2.5-D-CH-UD

Feed-through

ZK2.5-D-CH-DU

ZK2.5-D-CH2-DU-RL

GroundSection
2.5 mm²

12 AWG

Disconnect

ZK2.5-T3

ZK2.5-T1

With blade

ZK2.5-L-L-PE
ZK2.5-L-N-PE

With plug

ZK2.5-T1-PE

For 5x20 mm fuses

Aligned with
ZK2.5-SF

Section
2.5 mm²

12 AWG

Clamp -

ZK2.5-S

ZK2.5-S-4P

Channels for jumpering or testing -Test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

ZK2.5-SP

ZK2.5-SP-4P

Blown-fuse indicator

ZK2.5-SF

ZK2.5-SF-R1
ZK2.5-SF-R3

ZK2.5-S-R1

1SNK162020S0201 - Rev. B

2

2.5 mm²4 mm²
6 mm²
10 mm²ZK2.5 PI-Spring terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

1SNK162052V0014

Ordering details
Description
Feed-throughColor
2 connections

Type

Grey
Blue
OrangeYellow
Green
Red
White
Black

ZK2.5

Part Number

ZK2.5
ZK2.5-BL
ZK2.5-OR
ZK2.5-YL
ZK2.5-GN
ZK2.5-RD
ZK2.5-WH
ZK2.5-BK

1SNK705010R0000
1SNK705020R0000
1SNK705030R0000
1SNK705060R0000
1SNK705061R0000
1SNK705062R0000
1SNK705065R0000
1SNK705066R0000

UL - CSARail

Main technical dataIEC41.7 1.64"

49.2 1.94"

50.9 2"

5.2 mm 0.205 in spacing

Weight(1 pce) g

50
50
50
50
50
50
50
50

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

2

Mounting instructions

Connecting capacity

24.6 0.97"

Pkg
qty

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Shield connectors
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey

White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
20
1960
22
20
10

5.30
1.80
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
4.10
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5

Green-yellow

Type
ZK2.5-PE

Part Number
1SNK705150R0000

Pkg

Weightqty(1 pce) g

20

10.00

Technical data valid for copper conductors only.

PAGE 19

1SNK162023S0201

1ZK2.5-3P PI-Spring terminal blocks
Feed-through with 3 connections - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Find all the features of the ZK2.5 terminal block with the added option of distributing or branching 3 conductors.

Ordering details
Description
3 connections

ZK2.5-3PPart Number

ZK2.5-3P
ZK2.5-3P-BL
ZK2.5-3P-OR
ZK2.5-3P-YL
ZK2.5-3P-GN
ZK2.5-3P-RD
ZK2.5-3P-WH
ZK2.5-3P-BK

Main technical data49.2 1.94"

64.7 2.55"

24.6 0.97"

5.2 mm 0.205 in spacing

1SNK705011R0000
1SNK705021R0000
1SNK705031R0000
1SNK705067R0000
1SNK705068R0000
1SNK705069R0000
1SNK705072R0000
1SNK705073R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
50
50
50

7.40
7.40
7.40
7.40
7.40
7.40
7.40
7.40

Mounting instructions

Connecting capacity

41.7 1.64"

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
1960
22
20
10

5.30
2.40
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-3PTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK2.5-PE-3P

Part Number
1SNK705151R0000

Pkg

Weightqty(1 pce) g

20

11.90

1SNK162024S0201

2

Type

Grey
Blue
OrangeYellow
Green
Red
White
Black

1SNK162061V0014

Feed-throughColorZK2.5-4P PI-Spring terminal blocks
Feed-through with 4 connections - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Find all the features of the ZK2.5 terminal block with the added option of distributing or branching 4 conductors.

Ordering details
1SNK162070V0014

Description
Feed-throughColor
4 connections

Type

Grey
Blue
OrangeYellow
Green
Red
White
Black

ZK2.5-4P

Part Number

ZK2.5-4P
ZK2.5-4P-BL
ZK2.5-4P-OR
ZK2.5-4P-YL
ZK2.5-4P-GN
ZK2.5-4P-RD
ZK2.5-4P-WH
ZK2.5-4P-BK

1SNK705012R0000
1SNK705022R0000
1SNK705032R0000
1SNK705074R0000
1SNK705075R0000
1SNK705076R0000
1SNK705079R0000
1SNK705080R0000

UL - CSARail

Main technical data

5.2 mm 0.205 in spacing

41.7 1.64"

49.2 1.94"
40.1 1.58"

Weight(1 pce) g

50
50
50
50
50
50
50
50

9.00
9.00
9.00
9.00
9.00
9.00
9.00
9.00

Mounting instructions

Connecting capacity

80.2 3.16"

Pkg
qty

IEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

2

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
1960
22
20
10

5.30
2.70
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-4P

Green-yellow

Type
ZK2.5-PE-4P

Part Number
1SNK705152R0000

Pkg

Weightqty(1 pce) g

20

13.60

Technical data valid for copper conductors only.

PAGE 21

1SNK162025S0201

1

ZK4 PI-Spring terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

10 AWG

1SNK162033V0014

Ordering details
Description
Feed-throughColor
2 connections

Grey
Blue
OrangeYellow
Red
Black

2
ZK4

Type

Part Number

ZK4
ZK4-BLZK4-ORZK4-YLZK4-RDZK4-BK

1SNK706010R0000
1SNK706020R0000
1SNK706030R0000
1SNK706060R0000
1SNK706062R0000
1SNK706066R0000

Main technical data

6 mm 0.236 in spacing

42.6 1.68"

50.1 1.97"
29 1.14"Weight(1 pce) g

50
50
50
50
50
50

7.90
7.90
7.90
7.90
7.90
7.90

Mounting instructions

Connecting capacity
55.3 2.18"

Pkg
qty

IEC

UL - CSA

Rail
Wire stripping
length1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)32 A / 4 mm²
480 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

30 A / 10 AWG
636 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

9

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
1680
22
20
10

5.30
1.80
1.30
2.10
2.90
3.60
7.40
38.10
2.80
3.80
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK4

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK4-PEPart Number
1SNK706150R0000

Pkg

Weightqty(1 pce) g

20

12.60

1SNK162026S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK4-3P PI-Spring terminal blocks
Feed-through with 3 connections - 6 mm 0.236 in spacing
Description

4 mm²

Find all the features of the ZK4 terminal block with the added option of distributing or branching 3 conductors.

10 AWG

Ordering details

1SNK162037V0014

Description
Feed-throughColor
3 connections

50.1 1.97"
29 1.14"6 mm 0.236 in spacing

42.6 1.68"

72.5 2.58"

Part Number

ZK4-3P
ZK4-3P-BL
ZK4-3P-OR

1SNK706011R0000
1SNK706021R0000
1SNK706031R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey
Blue
OrangeMain technical data

Pkg

Weightqty(1 pce) g

50
50
50

11.00
11.00
11.00

Mounting instructions

Connecting capacity
ZK4-3PType

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)32 A / 4 mm²
480 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

30 A / 10 AWG
636 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

9

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
1680
22
20
10

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
2.80
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK4-3P

Green-yellow

Type
ZK4-PE-3PPart Number
1SNK706151R0000

Pkg

Weightqty(1 pce) g

20

15.70

Technical data valid for copper conductors only.

PAGE 23

1SNK162027S0201

1

ZK4-4P PI-Spring terminal blocks
Feed-through with 4 connections - 6 mm 0.236 in spacing
Description

4 mm²

Find all the features of the ZK4 terminal block with the added option of distributing or branching 4 conductors.

10 AWG

Ordering details
1SNK162041V0014

Description
Feed-throughColor
4 connections

Type

Grey
Blue
OrangePart Number

ZK4-4P
ZK4-4P-BL
ZK4-4P-OR

Main technical data

1SNK706012R0000
1SNK706022R0000
1SNK706032R0000

IEC

UL - CSA

Rail
Wire stripping
length

ZK4-4P

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

50.1 1.97"
46.2 1.82"

6 mm 0.236 in spacing

42.6 1.68"

89.7 3.53"

Weight(1 pce) g

50
50
50

13.80
13.80
13.80

Mounting instructions

Connecting capacity

2

Pkg
qty

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)32 A / 4 mm²
480 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

30 A / 10 AWG
636 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

9

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
1680
22
20
10

5.30
2.70
1.30
2.10
2.90
3.60
7.40
38.10
2.80
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK4-4P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK4-PE-4PPart Number
1SNK706152R0000

Pkg

Weightqty(1 pce) g

20

18.40

1SNK162028S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK6 PI-Spring terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

6 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.

8 AWG

1SNK162045V0014

Ordering details

ZK6

Description
Feed-through

Color

Type

2 connections

Grey
Blue
OrangeYellowRed
Black

Part Number

ZK6
ZK6-BLZK6-ORZK6-YLZK6-RDZK6-BK

1SNK708010R0000
1SNK708020R0000
1SNK708030R0000
1SNK708060R0000
1SNK708062R0000
1SNK708066R0000

Main technical data

8 mm 0.315 in spacing

43.4 1.71"

50.9 2"31 1.22"Weight(1 pce) g

50
50
50
50
50
50

11.80
11.80
11.80
11.80
11.80
11.80

2

Mounting instructions

Connecting capacity
57.5 2.26"

Pkg
qty

IEC

UL - CSA

Rail
Wire stripping
length1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1.5 mm²

24 ... 16 AWG

24 ... 10 AWG
24 ... 10 AWG

Tool (for flexible
conductor without
ferrule)41 A / 6 mm²
720 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

50 A / 8 AWG
1008 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 37 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

9

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
2.8 mm0.110 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
JB85-3
1SNK900603R0000
CS-R2
1SNK900106R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
40
20
10
20
20
20
10
10
1680
22
20
10

5.30
1.80
2.70
4.10
5.60
7.00
14.20
2.80
3.80
1.70
2.40
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK6

Green-yellow

Type
ZK6-PEPart Number
1SNK708150R0000

Pkg

Weightqty(1 pce) g

20

20.30

Technical data valid for copper conductors only.

PAGE 25

1SNK162029S0201

1

ZK6-3P PI-Spring terminal blocks
Feed-through with 3 connections - 8 mm 0.315 in spacing
Description

6 mm²

Find all the features of the ZK6 terminal block with the added option of distributing or branching 3 conductors.

8 AWG

Ordering details

1SNK162049V0014

Description
Feed-throughColor
3 connections

Grey
Blue
Orange250.9 2"31 1.22"8 mm 0.315 in spacing

43.4 1.71"

79.1 3.12"

Part Number

ZK6-3P
ZK6-3P-BL
ZK6-3P-OR

Main technical data

1SNK708011R0000
1SNK708021R0000
1SNK708031R0000

Pkg

Weightqty(1 pce) g

50
50
50

16.70
16.70
16.70

Mounting instructions

Connecting capacity
ZK6-3PTypeIEC

UL - CSA

Rail
Wire stripping
length1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1.5 mm²

24 ... 16 AWG

24 ... 10 AWG
24 ... 10 AWG

Tool (for flexible
conductor without
ferrule)41 A / 6 mm²
720 A

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

50 A / 8 AWG
1008 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 37 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

9

8

4
5
6
7
8
9

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
2.8 mm0.110 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK6-3P
1SNK708911R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
40
20
10
20
20
20
10
10
1680
22
20
10

5.30
2.80
2.70
4.10
5.60
7.00
14.20
2.80
6.40
1.70
2.40
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK6-3P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK6-PE-3PPart Number
1SNK708151R0000

Pkg

Weightqty(1 pce) g

20

21.50

1SNK162030S0201

1

ZK10 PI-Spring terminal blocks
Feed-through - 10 mm 0.394 in spacing
Description

10 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.
1SNK162072V0014

6 AWG

Ordering details
Description
Feed-throughColor
2 connections

Type

Part Number

ZK10
ZK10-BL
ZK10-OR

1SNK710010R0000
1SNK710020R0000
1SNK710030R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey
Blue
OrangeMain technical data

ZK10

10 mm 0.394 in spacing

49 1.93"56.5 2.22"
46.2 1.82"

Weight(1 pce) g

20
20
20

27.20
27.20
27.20

Mounting instructions

Connecting capacity

82.5 3.25"

Pkg
qty

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 mm²

20 ... 12 AWG

20 ... 8 AWG
20 ... 8 AWG

Tool (for flexible
conductor without
ferrule)57 A / 10 mm²1200 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

55 A / 6 AWG
1596 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 51 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

4
5
6

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)4 poles
76 A (IEC)
5 poles
76 A (IEC)
10 poles76 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeDark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
JB10-2
1SNK910302R0000
JB10-3
1SNK910303R0000
JB10-4
1SNK910304R0000
JB10-5
1SNK910305R0000
JB10-10
1SNK910310R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
40
30
20
20
20
20
1680
22
20
10

5.30
3.30
4.60
7.10
9.40
12.00
24.00
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10

Green-yellow

Type
ZK10-PEPart Number
1SNK710150R0000

Pkg

Weightqty(1 pce) g

20

36.20

Technical data valid for copper conductors only.

PAGE 27

1SNK162031S0201

1

ZK10-PV PI-Spring terminal blocks
Feed-through - 12 mm 0.472 in spacing
Description

10 mm²

Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– Compatible with JB12 jumpers to interconnect multiple terminal blocks.
1SNK162124V0014

6 AWG

Ordering details
Description

Color
2 connections

1SNK710063R0000
1SNK710065R0000

IEC

UL - CSA

Rail
Wire stripping
lengthTH 35-7.5,
TH 35-15
15 mm
0.591 inTool (for flexible
conductor without
ferrule)Flat screwdriverØ 4 mmØ 0.157 inMounting instructions

Connecting capacity

46.2 1.82"

12 mm 0.472 in spacing

49 1.93"56.5 2.22"

82.5 3.25"

Pkg Weight(1 pce) g
20
29.86
20
29.86

ZK10-PV
ZK10-PV-BL

Grey
Blue

Main technical data

ZK10-PV

Part Number

qty

Feed-through1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 AWG

20 ... 12 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

20 ... 8 AWG
20 ... 8 AWG

57 A / 10 mm²1200 A

55 A / 6 AWG
1596 A
100 kA
1000 V AC / 1500 V DC 1000 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

3

5

Description

2

Color

Type

Part Number

Pkg

Weight

50
50
50
20
20
20
20
22
20
1680
10

5.30
4.90
7.60
12.90
6.40
1.70
2.40
10.00
14.00
0.273
0.20

qty

1
2

End stops
Jumper bars

3
4

Circuit separators
Test adapters

5

Terminal block
markers

5.2 mm0.205 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank card

4

Dark grey
OrangeDark grey
Dark grey
White

Blank marker
Universal wire markers holder

Grey

BAZ1
JB12-2
JB12-3
JB12-5
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

1SNK900002R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000(1 pce) g

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may
modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK10-PEPart Number
1SNK710150R0000

Pkg

Weightqty(1 pce) g

20

36.20

1SNK162080S0201

2

Type

ZK10-3P PI-Spring terminal blocks
Feed-through with 3 connections - 10 mm 0.394 in spacing
Description

10 mm²–– Find all the features of the ZK10 terminal block with the added option of distributing or branching 3 conductors,–– ZK10-3P is perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC, 1000 V UL.

6 AWG

Ordering details
1SNK162095V0014

Description
Feed-throughColor
3 connections

10 mm 0.394 in spacing

49 1.93"56.5 2.22"
40.8 1.61"

1SNK710011R0000
1SNK710021R0000

IEC

UL - CSA

Rail
Wire stripping
lengthMain technical data

Pkg

Weightqty(1 pce) g

20
20

34.9
34.9

Mounting instructions

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 mm²

20 ... 12 AWG

96.3 3.79"

Part Number

ZK10-3P
ZK10-3P-BL

Grey
Blue

Connecting capacity
ZK10-3P

Type

20 ... 8 AWG
20 ... 8 AWG

Tool (for flexible
conductor without
ferrule)57 A / 10 mm²1200 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

56 A / 6 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 57 A - IM2 II 2 GD Ex eb I/II/IIIC

100 kA
1000 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)4 poles
76 A (IEC)
5 poles
76 A (IEC)
10 poles76 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card

Dark grey
Dark grey
OrangeDark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
JB10-2
1SNK910302R0000
JB10-3
1SNK910303R0000
JB10-4
1SNK910304R0000
JB10-5
1SNK910305R0000
JB10-10
1SNK910310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
40
30
20
20
20
1680
22
20
10

5.30
4.5
4.60
7.10
9.40
12.00
24.00
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10-3P

Green-yellow

Type
ZK10-PE-3P

Part Number
1SNK710151R0000

Pkg

Weightqty(1 pce) g

20

43.3

Technical data valid for copper conductors only.

PAGE 29

1SNK162061S0201

1

ZK10-3P-PV PI-Spring terminal blocks
Feed-through with 3 connections - 12 mm 0.472 in spacing

10 mm²

1SNK162126V0014

6 AWG

Description
Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– 3 connections configuration for easy grouping: 2 inputs / 1 output or 1 input / 2 outputs,–– Compatible with JB12 jumpers to interconnect multiple terminal blocks.
Description

Color

Feed-throughZK10-3P-PV

2

3 connections

Grey
Blue

Type

Part Number

Pkg Weightqty(1 pce) g

ZK10-3P-PV
ZK10-3P-PV-BL

1SNK710064R0000
1SNK710067R0000

20
20

Main technical data

Mounting instructions

Connecting capacity

40.8 1.61"

12 mm 0.472 in spacing

49 1.93"56.5 2.22"

96.3 3.79"

38.61
38.61

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

Wire stripping
length15 mm
0.591 inTool (for flexible
conductor
without ferrule)

Flat screwdriverØ 4 mmØ 0.157 in

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 4 AWG

20 ... 12 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

20 ... 8 AWG
20 ... 8 AWG

57 A / 10 mm²1200 A

56 A / 6 AWG
1596 A
100 kA
1000 V AC / 1500 V DC 1000 V
8000 V
IP20
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2

4
3
4

5

Type

Part Number

Pkg

Weight

50
50
50
20
20
20
20
22
20
1680
10

5.30
4.90
7.60
12.90
6.40
1.70
2.40
10.00
14.00
0.273
0.20

qty

1
2
3

Color

5

End stops
Jumper bars

5.2 mm0.205 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)
0.118 inCircuit separators 3 mm
For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
Blank card
Terminal block

Dark grey
OrangeDark grey
Dark greyWhitemarkers
Blank marker
Universal wire markers holder

Grey

BAZ1
JB12-2
JB12-3
JB12-5
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

1SNK900002R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000(1 pce) g

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK10-3P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK10-PE-3P

Part Number
1SNK710151R0000

Pkg

Weightqty(1 pce) g

20

43.3

1SNK162081S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify
the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK16 PI-Spring terminal blocks
Feed-through - 12 mm 0.472 in spacing
Description

16 mm²

Combine high performance with compact dimensions:–– 1000 V AC / DC IEC 600 V UL,–– Opt for the best marking visibility thanks to the up-front, flat marker zone, which lets you mark up to eight
digits or increase the font size.
1SNK162075V0014

4 AWG

Ordering details
Description
Feed-through

Color

Type

2 connections

Part Number

ZK16
ZK16-BL

1SNK712010R0000
1SNK712020R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey
Blue

Main technical data
ZK16

12 mm 0.472 in spacing

49 1.93"56.5 2.22"
46.2 1.82"

Weight(1 pce) g

20
20

33.80
33.80

Mounting instructions

Connecting capacity

82.5 3.25"

Pkg
qty

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 6 mm²

20 ... 10 AWG

20 ... 6 AWG
20 ... 6 AWG

Tool (for flexible
conductor without
ferrule)76 A / 16 mm²
1920 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

75 A / 4 AWG
2544 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 69 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC ExATEX

Haz Loc

IECEx

BV

DNV

Accessories
Description

2
1
2
3

3

4
4
5

5

6

6

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeDark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
JB12-2
1SNK912302R0000
JB12-3
1SNK912303R0000
JB12-5
1SNK912305R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
20
20
20
20
1680
22
20
10

5.30
3.30
4.90
7.60
12.90
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16

Green-yellow

Type
ZK16-PEPart Number
1SNK712150R0000

Pkg

Weightqty(1 pce) g

20

47.00

Technical data valid for copper conductors only.

PAGE 31

1SNK162032S0201

1

ZK16-PV PI-Spring terminal blocks
Feed-through - 14 mm 0.551 in spacing
Description

16 mm²

Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– No available jumpers for ZK16-PV and ZK16-3P-PV (14 mm spacing).
1SNK162128V0014

4 AWG

Ordering details
Description

Color
2 connections

1SNK712063R0000
1SNK712065R0000

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

Wire stripping
lengthFlexible with twin ferrule

0.5 ... 6 AWG

20 ... 10 AWG

Grey
Blue

Main technical data

ZK16-PV

1 conductor per
clamp

14 mm 0.551 in spacing

49 1.93"56.5 2.22"
46.2 1.82"

2 conductors
per clamp

Pkg

Weightqty(1 pce) g

15
15

36.56
36.56

Mounting instructions

Connecting capacity

82.5 3.25"

Part Number

ZK16-PV
ZK16-PV-BL

Feed-through20 ... 6 AWG
20 ... 6 AWG
Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

76 A / 16 mm²
1920 A
1000 V AC / 1500 V DC
8000 VIP20

TH 35-7.5,
TH 35-15
15 mm
0.591 inFlat screwdriverØ 4 mmØ 0.157 in

75 A / 4 AWG
2544 A
100 kA
1000 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

3

Description

2

4

1
2
3

End stops
Circuit separators
Test adapters

4

Terminal block
markersColor
5.2 mm0.205 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank card

Type

Dark grey
Dark grey
Dark grey
White

Blank marker
Universal wire markers holder

Grey

BAZ1
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

Part Number
1SNK900002R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000

Pkg

Weightqty(1 pce)  g

50
20
20
20
22
20
1680
10

5.30
6.40
1.70
2.40
10.00
14.00
0.273
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops. Some accessories such as jumper bars may modify
the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK16-PEPart Number
1SNK712150R0000

Pkg

Weightqty(1 pce) g

20

47.00

1SNK162082S0201

2

Type

ZK16-3P PI-Spring terminal blocks
Feed-through with 3 connections - 12 mm 0.472 in spacing
Description

16 mm²–– Find all the features of the ZK16 terminal block with the added option of distributing or branching 3 conductors,–– ZK16-3P is perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC, 1000 V UL.

4 AWG

Ordering details
1SNK162098V0014

Description
Feed-throughColor
3 connections

49 1.93"56.5 2.22"
40.8 1.61"

12 mm 0.472 in spacing

1SNK712011R0000
1SNK712021R0000

IEC

UL - CSA

Rail
Wire stripping
lengthMain technical data

Pkg

Weightqty(1 pce) g

20
20

44.3
44.3

Mounting instructions

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 6 mm²

20 ... 10 AWG

98.3 3.87"

Part Number

ZK16-3P
ZK16-3P-BL

Grey
Blue

Connecting capacity
ZK16-3P

Type

20 ... 6 AWG
20 ... 6 AWG

Tool (for flexible
conductor without
ferrule)76 A / 16 mm²
1920 ATH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

75 A / 4 AWG

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

Increased safety Ex e

693 V 76 A - IM2 II 2 GD Ex eb I/II/IIIC

100 kA
1000 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card

Dark grey
Dark grey
OrangeDark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
JB12-2
1SNK912302R0000
JB12-3
1SNK912303R0000
JB12-5
1SNK912305R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
20
20
20
1680
22
20
10

5.30
4.5
4.90
7.60
12.90
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16-3P

Green-yellow

Type
ZK16-PE-3P

Part Number
1SNK712151R0000

Pkg

Weightqty(1 pce) g

20

56.65

Technical data valid for copper conductors only.

PAGE 33

1SNK162063S0201

1

ZK16-3P-PV PI-Spring terminal blocks
Feed-through with 3 connections - 14 mm 0.551 in spacing
Description

16 mm²

1SNK162130V0014

4 AWG

Specially designed for high voltage utility scale solar power plants:–– Rated voltage of 1500 V DC IEC and 1000 V DC UL,–– Pre-mounted end section with light grey color specific to this application,–– Improved design with ribs to increase creepage distance,–– Compact solution only 2 mm thicker than normal product,–– 3 connections configuration for easy grouping: 2 inputs / 1 output or 1 input / 2 outputs,–– No available jumpers for ZK16-PV and ZK16-3P-PV (14 mm spacing).

Ordering details
Description

Color

Type

Part Number

Pkg Weight(1 pce) g
15
48.01
15
48.01
qty

Feed-through3 connections

2

ZK16-3P-PV
1SNK712064R0000
ZK16-3P-PV-BL 1SNK712067R0000

Grey
Blue

ZK16-3P-PV

Main technical data

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

Wire stripping
length15 mm
0.591 inTool (for flexible

Flat screwdriverØ 4 mmØ 0.157 in

40.8 1.61"

14 mm 0.551 in spacing

1 conductor per
clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

2 conductors per
clamp

Flexible with twin ferrule

0.5 ... 6 AWG

20 ... 10 AWG

49 1.93"56.5 2.22"

98.3 3.87"

20 ... 6 AWG
20 ... 6 AWG

76 A / 16 mm²
1920 A

75 A / 4 AWG
2544 A
100 kA
1000 V AC / 1500 V DC 1000 V
8000 V
IP20
NEMA 1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

conductor
without ferrule)

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

Accessories
1

3

Description

2

4

1
2
3
4

Color

End stops
5.2 mm0.205 inCircuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Terminal block Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type
BAZ1
CS-R3
TP2
TP4
MC812
MC812PA
MG-CPM 13 41791
UMH

Part Number
1SNK900002R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK160000R0000
1SNK169999R0000
1SNB041791R0612
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
22
20
1680
10

5.30
6.40
1.70
2.40
10.00
14.00
0.273
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK16-3P

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK16-PE-3P

Part Number
1SNK712151R0000

Pkg

Weightqty(1 pce) g

20

56.65

1SNK162083S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-PE PI-Spring terminal blocks
Ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162081V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5.

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK2.5-PE

1SNK705150R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp

57.4 2.26"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length49.2 1.94"

5.2 mm 0.205 in spacing

41.7 1.64"

Tool (for flexible

24.6 0.97"

Weight(1 pce) g

20

10.00

Mounting instructions

Connecting capacity
ZK2.5-PEPkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
CS-R2
1SNK900106R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

5.30
1.80
3.80
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162039S0201

1

Technical data valid for copper conductors only.

PAGE 35

ZK2.5-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162069V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-3P.

Ordering details
Description

Color
3 connections

GroundTypePart Number

Green-yellow

ZK2.5-PE-3P

IEC

UL - CSA

Main technical data

ZK2.5-PE-3P

1SNK705151R0000

Rail

2

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthTool (for flexible

41.7 1.64"

49.2 1.94"

71.2 2.8"

Weight(1 pce) g

20

11.90

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

24.6 0.97"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

5.30
2.40
6.40
0.23
9.00
10.00
0.20

1SNK162040S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-PE-4P PI-Spring terminal blocks
Ground with 4 connections - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162032V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-4P.

Ordering details
Description
4 connections

Ground
ZK2.5-PE-4P

Color

Type

Part Number

Green-yellow

ZK2.5-PE-4P

1SNK705152R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp
41.7 1.64"

49.2 1.94"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthTool (for flexible
conductor without
ferrule)40.1 1.58"

5.2 mm 0.205 in spacing

Weight(1 pce) g

20

13.60

Mounting instructions

Connecting capacity
86.7 3.41"

Pkg
qty

Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

5.30
2.70
6.40
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162041S0201

1

Technical data valid for copper conductors only.

PAGE 37

ZK4-PE PI-Spring terminal blocks
Ground - 6 mm 0.236 in spacing
Description

4 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK4.
1SNK162036V0014

10 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK4-PE

1SNK706150R0000

IEC

UL - CSA

Rail

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

Wire stripping
lengthMain technical data
ZK4-PE

1 conductor
per clamp
62.7 2.47"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
26 ... 12 AWG

6 mm 0.236 in spacing

42.6 1.68"

Tool (for flexible

29 1.14"Weight(1 pce) g

20

12.60

Mounting instructions

Connecting capacity

50.1 1.97"

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
CS-R2
1SNK900106R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
1.80
3.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162042S0201

2

Pkg
qty

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK4-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 6 mm 0.236 in spacing
Description

4 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK4-3P.
1SNK162040V0014

10 AWG

Ordering details
Description

Color
3 connections

GroundTypePart Number

Green-yellow

ZK4-PE-3P

1SNK706151R0000

IEC

UL - CSA

Rail

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

Wire stripping
lengthMain technical data

ZK4-PE-3P

50.1 1.97"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
26 ... 12 AWG

42.6 1.68"

79 3.11"Weight(1 pce) g

20

15.70

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

29 1.14"6 mm 0.236 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
2.40
6.40
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162043S0201

1

Technical data valid for copper conductors only.

PAGE 39

ZK4-PE-4P PI-Spring terminal blocks
Ground with 4 connections - 6 mm 0.236 in spacing
Description

4 mm²

1SNK162044V0014

10 AWG

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK4-4P.

Ordering details
Description
4 connections

GroundZK4-PE-4P

ColorPart Number

Green-yellow

ZK4-PE-4P

IEC

UL - CSA

Rail

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

Wire stripping
lengthMain technical data

96.2 3.79"

42.6 1.68"

50.1 1.97"

1 conductor
per clamp

1SNK706152R0000

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)46.2 1.82"

6 mm 0.236 in spacing

Pkg

Weightqty(1 pce) g

20

18.40

Mounting instructions

Connecting capacity
2

Type

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-4P
1SNK705912R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
2.70
6.40
0.27
10.00
11.00
0.20

1SNK162044S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK6-PE PI-Spring terminal blocks
Ground - 8 mm 0.315 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK6.
1SNK162048V0014

8 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK6-PE

1SNK708150R0000

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp
64.6 2.54"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

24 ... 10 AWG
24 ... 10 AWG

50.9 2"8 mm 0.315 in spacing

43.4 1.71"

Tool (for flexible

31 1.22"Weight(1 pce) g

20

20.30

Mounting instructions

Connecting capacity

ZK6-PEPkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

8 AWG
1008 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5
1SNK705910R0000
CS-R2
1SNK900106R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
1.80
3.80
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162045S0201

1

Technical data valid for copper conductors only.

PAGE 41

ZK6-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 8 mm 0.315 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK6-3P.
1SNK162082V0014

8 AWG

Ordering details
Description

Color
3 connections

GroundTypePart Number

Green-yellow

ZK6-PE-3P

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²

24 ... 8 AWG

Wire stripping
lengthMain technical data

ZK6-PE-3P

1SNK708151R0000

2

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

24 ... 10 AWG
24 ... 10 AWG

43.4 1.71"

50.9 2"

Weight(1 pce) g

20

21.50

Mounting instructions

Connecting capacity

85.6 3.37"

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

8 AWG
1008 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

31 1.22"8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK6-3P
1SNK708911R0000
CS-R3
1SNK900107R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

5.30
2.80
6.40
0.27
10.00
14.00
0.20

1SNK162046S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK10-PE PI-Spring terminal blocks
Ground - 10 mm 0.394 in spacing
Description

10 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK10.
1SNK162083V0014

6 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK10-PE

1SNK710150R0000

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

Wire stripping
lengthMain technical data

ZK10-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 8 AWG
20 ... 8 AWG

Tool (for flexible

49 1.9"56.5 2.2"

87.7 3.45"

Weight(1 pce) g

20

36.20

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

46.2 1.18"

10 mm 0.394 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

5

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
20
1680
22
20
10

5.30
3.30
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162047S0201

1

Technical data valid for copper conductors only.

PAGE 43

ZK10-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 10 mm 0.394 in spacing
Description

10 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 standard,–– Secured snap on or off the rail,–– Profile aligned with ZK10-3P.
1SNK162097V0014

6 AWG

Ordering details
Description

Color
3 connections

GroundType

Green-yellow

ZK10-PE-3P

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²

20 ... 6 AWG

Wire stripping
lengthMain technical data

ZK10-PE-3P

Part Number
1SNK710151R0000

2

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 8 AWG
20 ... 8 AWG

49 1.93"56.5 2.22"

Weight(1 pce) g

20

43.3

Mounting instructions

Connecting capacity

99.1 3.87"

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC

TH 35-7.5,
TH 35-15
15 mm
0.591 inFlat screwdriverØ 4 mmØ 0.157 in

40.8 1.61"

10 mm 0.394 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories
1

3

Description

2
1
2
3

End stops
End sections
Test adapters

4

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
1680
22
20
10

5.30
4.5
1.70
2.40
0.27
10.00
14.00
0.20

1SNK162062S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK16-PE PI-Spring terminal blocks
Ground - 12 mm 0.472 in spacing
Description

16 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK16.
1SNK162084V0014

4 AWG

Ordering details
Description

Color
2 connections

GroundTypePart Number

Green-yellow

ZK16-PE

1SNK712150R0000

IEC

UL - CSA

Rail

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

Wire stripping
lengthMain technical data

ZK16-PE56.5 2.22"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 6 AWG
20 ... 6 AWG

49 1.93"87.7 3.45"

Weight(1 pce) g

20

47.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG
2544 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
15 mm
0.591 in2

Flat screwdriverØ 4 mmØ 0.157 in

46.2 1.82"

12 mm 0.472 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

5

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Terminal block
markersColor
5.2 mm0.205 in
2 mm
0.079 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10
1SNK710910R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
20
1680
22
20
10

5.30
3.30
6.40
1.70
2.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162048S0201

1

Technical data valid for copper conductors only.

PAGE 45

ZK16-PE-3P PI-Spring terminal blocks
Ground with 3 connections - 12 mm 0.472 in spacing
Description

16 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 standard,–– Secured snap on or off the rail,–– Profile aligned with ZK16-3P.
1SNK162100V0014

4 AWG

Ordering details
Description

Color
3 connections

GroundType

Green-yellow

ZK16-PE-3P

IEC

UL - CSA

Rail

0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²

20 ... 4 AWG

Wire stripping
lengthMain technical data

ZK16-PE-3P

Part Number
1SNK712151R0000

2

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

20 ... 6 AWG
20 ... 6 AWG

49 1.93"56.5 2.22"
40.8 1.61"

Weight(1 pce) g

20

56.65

Mounting instructions

Connecting capacity
101.1 3.98"

Pkg
qty

Tool (for flexible
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG
2544 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC

TH 35-7.5,
TH 35-15
15 mm
0.591 inFlat screwdriverØ 4 mmØ 0.157 in

12 mm 0.472 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BV

Accessories
1

3

Description

2
1
2
3

End stops
End sections
Test adapters

4

Terminal block
markers4Color
5.2 mm0.205 in
2 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK10-3P
1SNK710911R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
1680
22
20
10

5.30
4.5
1.70
2.40
0.27
10.00
14.00
0.20

1SNK162064S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-S PI-Spring terminal blocks
Disconnect with blade - with test sockets - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162085V0014

12 AWG

Description
Combine high performance with compact dimensions: 630 V IEC 300 V UL.
Secure the current measurement:–– for currents below 50 mA, thanks to 2 built in test points DIA 2 mm 0.079 in,–– for currents up to 16 A, by using the TP4 test adapter inserted into the jumper channels.

Ordering details
Description

Colorwith 2 test sockets DIA 2 mm
0.079 in

Disconnect

Type

Grey
Blue
Orange

ZK2.5-S
ZK2.5-S-BL
ZK2.5-S-OR

1SNK705310R0000
1SNK705320R0000
1SNK705330R0000

UL - CSARail

Main technical data

5.2 mm 0.205 in spacing

60.1 2.37"
52.6 2.07"

53.3 2.1"
45.8 1.8"
27.9 1.10"

IEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

65.7 2.59"

Pkg

Weightqty(1 pce) g

50
50
50

8.10
8.10
8.10

Mounting instructions

Connecting capacity

ZK2.5-SPart Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

20 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mounted with
fixed foot on top (power side) so that the disconnect knife does not partially close through gravity. Furthermore,as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary disconnection
at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Shield connectors
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
20
1960
22
20
10

5.30
2.40
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
4.10
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162036S0201

1

Technical data valid for copper conductors only.

PAGE 47

ZK2.5-S-4P PI-Spring terminal blocks
Disconnect with blade - with test socket - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162103V0014

12 AWG

ZK2.5-S-4P

Description–– Combine high performances with compact dimensions: 630 V IEC 300 V UL,–– Simplify the measurement with 1 built in test point DIA 2 mm 0.079 in (for current below 50mA) and TP... test
adapter inserted into one jumper channel,–– Clear marking visibility with SNK top marking location 20% enlarged.

Ordering details
Description

Colorwith 1 test socket DIA 2 mm
0.079 in

Disconnect

Type

Grey
Blue
Orange

ZK2.5-S-4P
ZK2.5-S-4P-BL
ZK2.5-S-4P-OR

Main technical data

53.2 2.1"
45.8 1.8"
59.5 2.34"
52 2.05"

86.1 3.39"

38.8 1.53"

5.2 mm 0.205 in spacing

1SNK705312R0000
1SNK705321R0000
1SNK705331R0000

Pkg

Weightqty(1 pce) g

50
50
50

11.14
11.14
11.14

Mounting instructions

Connecting capacity

2

Part NumberIEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

20 A / 2.5 mm²
300 A

20 A / 12 AWG

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mounted with
fixed foot on top (power side) so that the disconnect knife does not partially close through gravity. Furthermore,as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary disconnection
at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

4
5
6
7

Color

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

1SNK162069S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-S-R1 PI-Spring terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing
Description

2.5 mm²

Simplify the distribution of circuits in marshalling cabinets thanks to our disconnect terminal blocks with thesame profile as ZK2.5-SF fuse.

12 AWG

Ordering details
Description

1SNK162088V0014

55.4 2.18"

48.6 1.91"

62.9 2.48"

56.1 2.21"
24.6 0.97"

Part Number

ZK2.5-S-R1

1SNK706310R0000

UL - CSA

Rail

Pkg

Weightqty(1 pce) g

50

8.90

Mounting instructions

Connecting capacity

2 conductors
per clamp

6 mm 0.236 in spacing

Grey

Main technical data
1 conductor
per clamp

63.1 2.48"

Type

Profile aligned with ZK2.5-SF

Disconnect

ZK2.5-S-R1

Color

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthFlexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

2

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

20 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mounted with
fixed foot on top (power side) so that the disconnect knife does not partially close through gravity. Furthermore,as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary disconnection
at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
20
20
20
10
10
1680
22
20
10

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

PI-Spring terminal blocks
Description

ZK4-3P

ZK2.5-SF

Feed-through
Fuse

Color
Grey
Grey, dark grey

Type
ZK4-3P
ZK2.5-SF

Part Number
1SNK706011R0000
1SNK706410R0000

Pkg

Weightqty(1 pce) g

50
50

11.00
16.20

Technical data valid for copper conductors only.

PAGE 49

1SNK162037S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-SP PI-Spring terminal blocks
Disconnect with plug - with test sockets - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
The flexible solution for fitting the component of your choice in series with our quick-fitting PG5 component
holder plug:–– compatible with components of 8.8 x 3.2 mm 0.346 x 0.125 in, such as resistors, diodes or mini axial fuses.

1SNK162089V0014

Ordering details
Description

Colorwith 2 test sockets DIA 2 mm
0.079 in

Disconnect

Grey

ZK2.5-SP43.1 1.69"

50.6 1.99"

65.7 2.59"

ZK2.5-SP

Main technical data

Part Number
1SNK705311R0000

Pkg

Weightqty(1 pce) g

50

11.50

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

17 A / 2.5 mm²
300 A

18 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 127.9 1.10"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

5.2 mm0.205 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
4 Circuit separators 3 mm
0.118 in
5 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
6 Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
7 Shield connectors
8 Component plugs Components in series with circuit
9 Disconnect plugs Equipped with linking bar
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Dark grey
Orange
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBP
1SNK900601R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
20
20
20
1960
22
20
10

5.30
2.40
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
4.10
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK162038S0201

2

Type

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-SP-4P PI-Spring terminal blocks
Disconnect with plug - with test socket - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
The flexible solution for fitting the component of your choice in series with our quick-fitting PG5 component
holder plug:–– compatible with components of 8.8 x 3.2 mm 0.346 x 0.125 in, such as resistors, diodes or mini axial fuses.

1SNK162106V0014

Ordering details
Description

Color

Type

with 1 test socket DIA 2 mm
0.079 in

Disconnect

Grey

ZK2.5-SP-4P

1SNK705313R0000

UL - CSARail

Main technical data

50.6 1.99"
43.1 1.7"
38.8 1.53"

5.2 mm 0.205 in spacingIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

86.1 3.39"

Pkg

Weightqty(1 pce) g

50

10.67

Mounting instructions

Connecting capacity

ZK2.5-SP-4P

Part Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

17 A / 2.5 mm²
300 A

18 A / 12 AWG

630 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Component plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
20
20
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162070S0201

9

Color

Technical data valid for copper conductors only.

PAGE 51

ZK2.5-SF PI-Spring terminal blocks
For 5x20 fuses - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description
Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the 2 jumper channels aligned with ZK4-3P feed-through and ZK2.5-S-R1
disconnect terminal blocks.

Ordering details
1SNK162090V0014

Description

Color

Fuse

Type

Grey, dark grey

ZK2.5-SFIEC

UL - CSA

Main technical data

74 2.91"

81.5 3.21"

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-SF

63.1 2.48"

1SNK706410R0000

Pkg

Weightqty(1 pce) g

50

16.20

Mounting instructions

Connecting capacity
2

Part Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

6.3 A / 2.5 mm²

16 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 V
IP20

300 V

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The fuse holder must be first disconnected prior any fuse replacement. Mount your fuse safely without touching
any active part: put the fuse into the hooks of the fuse holder shutter; at the closing of the shutter, the fuse isperfectly in place in the fuse holder.
24.6 0.97"

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

6 mm 0.236 in spacing

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

1

3

4

5

6

7

Description

2

8

1
2
3

4
5
6
7
8

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
20
20
20
10
10
1680
22
20

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK162021S0201

Accessories

ZK2.5-SF-R PI-Spring terminal blocks
For 5x20 fuses - with blown fuse indicator - 6 mm 0.236 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the 2 jumper channels aligned with ZK4-3P feed-through and ZK2.5-S-R1
disconnect terminal blocks,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

1SNK162091V0014

Ordering details
Description

Color

Type

Fuse with blown fuse indicator 24 ... 110 V AC / DC Grey, dark greywith blown fuse indicator 115 ... 250 V AC / DC

ZK2.5-SF-R1
ZK2.5-SF-R3

1SNK706411R0000
1SNK706412R0000

UL - CSARail

Main technical data

Pkg

Weightqty(1 pce) g

50
50

16.30
16.30

Mounting instructions

Connecting capacity
ZK2.5-SF-R

Part NumberIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

24.6 0.97"

6 mm 0.236 in spacing

74 2.91"

81.5 3.21"

63.1 2.48"

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

6.3 A / 2.5 mm²

16 A / 12 AWG
396 A

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 VIP20

300 V

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The fuse holder must be first disconnected prior any fuse replacement. Mount your fuse safely without touching
any active part: put the fuse into the hooks of the fuse holder shutter; at the closing of the shutter, the fuse isperfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

1

3

4

5

6

7

Description

2

8

1
2
3

4
5
6
7
8

5.2 mm0.205 in
2 mm
0.079 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Color
Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-3P
1SNK705911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
20
20
20
10
10
1680
22
20

5.30
2.40
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

PAGE 53

1SNK162022S0201

Accessories

ZK2.5-D2 PI-Spring terminal blocks
Double deck with 2 feed-through circuits - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Combine high performance with compact dimensions:–– 800 V IEC 600 V UL,–– 2 jumper channels and a large input and output marker zone on each deck.

Ordering details
1SNK162060V0014

Description
Feed-throughColor
2 feed-through circuits

Grey
Blue

ZK2.5-D2

44.6 1.76"

5.2 mm 0.205 in spacing

61.7 2.43"

69.2 2.72"

78.5 3.09"

Part Number

ZK2.5-D2
ZK2.5-D2-BL

Main technical data

1SNK705210R0000
1SNK705220R0000

Pkg

Weightqty(1 pce) g

50
50

11.20
11.20

Mounting instructions

Connecting capacity
2

Type

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC ExATEX

Haz Loc

IECEx

BV

DNV

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-D2 and ZK2.5-D1

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZK2.5-D1-PE

Part Number
1SNK705250R0000

Pkg

Weightqty(1 pce) g

20

15.70

1SNK162033S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-D1 PI-Spring terminal blocks
Double deck with 1 feed-through circuit - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Find the same functionalities as ZK2.5-D2 and ease one potential distribution on 4 independent connections.

Ordering details
Description

1SNK162078V0014

Feed-through

ZK2.5-D1

61.7 2.43"

69.2 2.72"

78.5 3.09"

Color

Type

1 feed-through circuit

Grey

Part Number

ZK2.5-D1

1SNK705211R0000

UL - CSARail

Main technical data

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacityIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

2
conductor without
ferrule)24 A / 2.5 mm²
300 A

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

20 A / 12 AWG
396 A
100 kA
600 V

Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

44.6 1.76"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Profile aligned with ZK2.5-D2 and ZK2.5-D1

Green-yellow

Type
ZK2.5-D1-PE

Part Number
1SNK705250R0000

Pkg

Weightqty(1 pce) g

20

15.70

Technical data valid for copper conductors only.

PAGE 55

1SNK162035S0201

1ZK2.5-D2-PE PI-Spring terminal blocks
Double deck with 1 feed-through circuit and 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162079V0014

12 AWG

Description
Combine high performance with compact dimensions:–– 800 V IEC 600 V UL,–– 1 feed through circuit and 1 ground circuit in just 5.2 mm 0.205 in spacing,–– 2 jumper channels and a large input and output marker zone on each deck,–– designed for easy wiring.

Ordering details
Description

Color

Feed-through + 1 feed-through circuit and 1 groundcircuitgroundTypePart Number

Grey,Green-yellow

ZK2.5-D2-PE

IEC

UL - CSA

Main technical data

44 1.73"

5.2 mm 0.205 in spacing

61.7 2.43"

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

84.6 3.33"

Weight(1 pce) g

20

15.70

Mounting instructions

Connecting capacity

ZK2.5-D2-PE

69.2 2.72"

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

800 V
8000 VIP20

600 V

Increased safety Ex e

693 V 21 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

IECEx

ATEX

Haz Loc

BV

DNV

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through PI-Spring terminal blocks
Description
Feed-throughTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color

Type
Grey

ZK2.5-D2

Part Number
1SNK705210R0000

Pkg

Weightqty(1 pce) g

50

11.20

1SNK162034S0201

2

1SNK705212R0000

Pkg
qty

ZK2.5-D1-PE PI-Spring terminal blocks
Double deck with 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162080V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-D2.

Ordering details
DescriptionColor
1 ground circuit

GroundTypePart Number

Green-yellow

ZK2.5-D1-PE

1SNK705250R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp
84.6 3.33"

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length

5.2 mm 0.205 in spacing

61.7 2.43"

69.2 2.72"

Tool (for flexible

44 1.73"

Weight(1 pce) g

20

15.70

Mounting instructions

Connecting capacity
ZK2.5-D1-PE

Pkg
qty

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC – Class I, Zone 1, AEx e II, Ex e II U

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

Haz Loc

BV

DNV

Accessories

3

5

7

Description

2
1
2
3

End stops
End sections
Test adapters

4

Test connectors

5
6
7

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card

4

6

Color
10 mm
0.394 in
2 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Universal wire markers holder

Dark grey
Dark grey
Dark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162049S0201

1

Technical data valid for copper conductors only.

PAGE 57

ZK2.5-T3 PI-Spring terminal blocks
Triple deck with 3 feed-through circuits - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Combine high performance with compact dimensions in just 5.2 mm 0.205 in spacing:–– 500 V IEC 300 V UL,–– 1 jumper channel and a large input and output marker zone on each deck.

Ordering details
1SNK162109V0014

Description

2

Feed-through74.7 2.91"

82.2 3.22"

Type

3 feed-through circuits

Grey

ZK2.5-T3

Main technical data

Part Number
1SNK705510R0000

Pkg

Weightqty(1 pce) g

25

17.33

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-T3

99.6 3.89"

Color

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.9 1.73"

CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

5.2 mm 0.205 in spacing

Accessories
1

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Ground PI-Spring terminal blocks
Description
GroundTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSColorGreen-yellow

Type
ZK2.5-T1-PE

Part Number
1SNK705550R0000

Pkg

Weightqty(1 pce) g

25

21.53

1SNK162075S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZK2.5-T1 PI-Spring terminal blocks
Triple deck with 1 feed-through circuit - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Find the same functionalities as ZK2.5-T3 and ease one potential distribution on 6 independent connections.

Ordering details
Description

1SNK162110V0014

Feed-through

ZK2.5-T1

74.7 2.91"

82.2 3.22"

99.6 3.89"

Color

Type

1 feed-through circuit

Grey

Part Number

ZK2.5-T1

1SNK705511R0000

UL - CSARail

Main technical data

Pkg

Weightqty(1 pce) g

25

17.33

Mounting instructions

Connecting capacityIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

44.9 1.73"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground PI-Spring terminal blocks
Description
GroundColor
Green-yellow

Type
ZK2.5-T1-PE

Part Number
1SNK705550R0000

Pkg

Weightqty(1 pce) g

25

21.53

Technical data valid for copper conductors only.

PAGE 59

1SNK162076S0201

1ZK2.5-L-L-PE PI-Spring terminal blocks
Triple deck with 2 feed-through circuits and 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162112V0014

12 AWG

Description
Combine high performance with compact dimensions:–– 500V IEC 300 V UL,–– 2 feed through circuits and 1 ground circuit in just 5.2 mm 0.205 in spacing,–– 1 jumper channel and a large input and output marker zone on each deck,–– designed for easy wiring.

Ordering details
Description

Color

Feed-through + 2 feed-through circuits and 1
ground circuit
groundType

Grey,Green-yellow

ZK2.5-L-L-PE

IEC

UL - CSA

Main technical data
ZK2.5-L-L-PE

5.2 mm 0.205 in spacing

74.7 2.91"

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

101.9 3.97"

44.9 1.73"

1SNK705512R0000

Pkg

Weightqty(1 pce) g

25

21.38

Mounting instructions

Connecting capacity

82.2 3.22"

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

IECEx

ATEX

BV

Accessories
1

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through PI-Spring terminal blocks
Description
Feed-throughTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color

Type
Grey

ZK2.5-T3

Part Number
1SNK705510R0000

Pkg

Weightqty(1 pce) g

25

17.33

1SNK162078S0201

2

Part Number

ZK2.5-L-N-PE PI-Spring terminal blocks
Triple deck with 2 feed-through circuits and 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162113V0014

12 AWG

Description
Combine high performance with compact dimensions:–– 500 V IEC 300 V UL,–– 2 feed through circuits, phase and neutral, and 1 ground circuit in just 5.2 mm 0.205 in spacing,–– 1 jumper channel and a large input and output marker zone on each deck,–– designed for easy wiring.

Ordering details
Description

Color

Feed-through + 2 feed-through circuits and 1
ground circuit
groundTypeBlue, grey,
Green-yellow

ZK2.5-L-N-PE

1SNK705513R0000

IEC

UL - CSARail

Main technical data
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

44.9 1.73"

5.2 mm 0.205 in spacing

74.7 2.91"

82.2 3.22"

101.9 3.97"

Pkg

Weightqty(1 pce) g

25

21.38

Mounting instructions

Connecting capacity

ZK2.5-L-N-PE

Part Number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A

20 A / 12 AWG
396 A

500 V
8000 VIP20

300 V

Increased safety Ex e

440 V 20 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

IECEx

ATEX

BV

Accessories

3

4

5

6

7

Description

2
1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5

Test connectors

6
7

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through PI-Spring terminal blocks
Description
Feed-through

Color

Type
Grey

ZK2.5-T3

Part Number
1SNK705510R0000

Pkg

Weightqty(1 pce) g

25

17.33

Technical data valid for copper conductors only.

PAGE 61

1SNK162079S0201

1ZK2.5-T1-PE PI-Spring terminal blocks
Triple deck with 1 ground circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK162111V0014

12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of the IEC 60947-7-2 terminal block standard,–– Secured snap on or off the rail,–– Profile aligned with ZK2.5-T3,–– 1 jumper channel on bottom and middle decks.

Ordering details
DescriptionColor
1 ground circuit

GroundType

Green-yellow

ZK2.5-T1-PE

IEC

UL - CSA

Main technical data
ZK2.5-T1-PE

1 conductor
per clamp
101.9 3.97"

1SNK705550R0000

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

RailWire stripping
length

5.2 mm 0.205 in spacing

74.7 2.91"

Tool (for flexible

44.9 1.73"

Pkg

Weightqty(1 pce) g

25

21.53

Mounting instructions

Connecting capacity

82.2 3.22"

conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/IIC/IIIC

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Test adapters

4

Test connectors

5
6

Label holders
Terminal block
markers

4

6

Color
10 mm
0.394 in
0.8 mm
0.031 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey
Dark grey
Dark grey
Dark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-T3
1SNK705961R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
20
20
10
10
100
1960
22
20
10

24.00
4.76
1.70
2.40
5.20
5.20
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162077S0201

2

Part Number

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-CH-4P-LR PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuit with one 1N4007 diode,–– Clear identification of the diode orientation with marking identification on the top of the terminal block

1SNK162107V0014

Ordering details
Description

Colorwith 1 test socket DIA 2 mm
0.079 inComponent
holderGrey

ZK2.5-CH-4P

50.6 1.99"
43.1 1.7"

1SNK705710R0000

UL - CSA

Rail

Pkg

Weightqty(1 pce) g

50

10.91

Mounting instructions
IEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

86.1 3.39"

38.8 1.53"

Part Number

ZK2.5-CH-4P-LR

Main technical data
Connecting capacity

5.2 mm 0.205 in spacingTypeconductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 A / 2.5 mm²

1 A / 12 AWG

630 V

300 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.433 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3
4

5

6

7

4
5
6
7

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162071S0201

3

Color

Technical data valid for copper conductors only.

PAGE 63

ZK2.5-CH-4P-RL PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuit with one 1N4007 diode,–– Clear identification of the diode orientation with marking identification on the top of the terminal block

1SNK162108V0014

Ordering details
Description

Colorwith 1 test socket DIA 2 mm
0.079 inComponent
holderGrey

ZK2.5-CH-4P

50.6 1.99"
43.1 1.7"
38.8 1.53"

Part Number
1SNK705711R0000

Pkg

Weightqty(1 pce) g

50

10.91

Mounting instructions
IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

86.1 3.39"

5.2 mm 0.205 in spacing

ZK2.5-CH-4P-RL

Main technical data
Connecting capacity

2

Type

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 A / 2.5 mm²

1 A / 12 AWG

630 V

300 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

4
5
6
7

Color

5.2 mm0.205 in
2 mm
0.158 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZ1
1SNK900002R0000
EK2.5-S-4P
1SNK705913R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
1960
22
20
10

5.30
2.94
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
0.23
9.00
10.00
0.20

1SNK162072S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-D-CH-UD PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details

1SNK162101V0014

Description
Component
holder2 conductors
per clamp

61.7 2.43"

Grey

Part Number

ZK2.5-D-CH-UD

1SNK705213R0000

UL - CSA

Rail

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacity

ZK2.5-D-CH

69.2 2.72"

Type

Main technical data
1 conductor
per clamp

78.5 3.09"

Color

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
lengthFlexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

2

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A

20 A / 12 AWG

800 V

600 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.443 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.6 1.76"

CE

RoHS

USR CNR

CSA

EAC

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162066S0201

1

Technical data valid for copper conductors only.

PAGE 65

ZK2.5-D-CH-DU PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details

1SNK162102V0014

Description
Component
holder

61.7 2.43"

Grey

ZK2.5-D-CH-DU

Part Number
1SNK705214R0000

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-D-CH

69.2 2.72"

Type

Main technical data

2

78.5 3.09"

Color

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A

20 A / 12 AWG

800 V

600 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.443 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
44.6 1.76"

CE

RoHS

USR CNR

CSA

EAC

5.2 mm 0.205 in spacing

Accessories
1

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

1SNK162067S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZK2.5-D-CH2-DU-RL PI-Spring terminal blocks
Component holder - 5.2 mm 0.205 in spacing
2.5 mm²
12 AWG

Description–– Protect your circuit with 1N4007 diodes;–– Convenient identification of the diodes orientation on the terminal block front side.

Ordering details

1SNK162114V0014

Description
Component
holder

61.7 2.43"

69.2 2.72"
44.6 1.76"

Type
ZK2.5-D-CH2-DU-RL

GreyMain technical data

Part Number
1SNK705219R0000

Pkg

Weightqty(1 pce) g

50

11.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

ZK2.5-D-CH2

78.5 3.09"

Color

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 A / 2.5 mm²/ 12 AWG

800 V

600 V

IP20

NEMA 1

TH 35-7.5,
TH 35-15
11 mm
0.443 in2

Flat screwdriverØ 3.5 mm
Ø 0.138 in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing

CE

RoHS

EAC

Accessories

3

4

5

6

7

Description

2

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in
2 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7

Shield connectors
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
EK2.5-D2
1SNK705960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
1960
22
20
10

24.00
3.40
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK162073S0201

1

Technical data valid for copper conductors only.

PAGE 67

Summary_3

3

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
Pluggable technology

Technologies presentation			

70

Overview				

76

3

PI-Spring Pluggable
Pluggable Pluggable
2.5 mm² / 12 AWG

Feed-throughZD2.5-11
ZD2.5-2280
81

Ground

ZD2.5-22-PE

82

Feed-through		

ZDK2.5-11
ZDK2.5-21
ZDK2.5-22

83
84
85

4 mm² / 10 AWG

Feed-throughZDK4-2286

2.5 mm² / 12 AWG

GroundZDK2.5-11-PE
ZDK2.5-22-PE

87
88

Double deck

ZDK2.5-D2
ZDK2.5-D1
ZDK2.5-D2-PE

89
90
91

		

ZDK2.5-D1-PE

92

PI-Spring female plugs

CDK2.5
CDK2.5-J
CDK2.5-2P-J
CDK4

93
94
95
96

4 mm² / 10 AWG
Feed-through		

ZDS4-22
ZDS4-22-R1

98
100

Screw clamp female plugs

CDS4
CDS4-R1

99
101

PI-Spring Pluggable
2.5 mm² / 12 AWG

		Summary_3

Screw clamp Pluggable

PAGE 69Pluggable technology - SNK series, terminal blocks
Features and benefits

The SNK series pluggable terminal blocks combine the benefits of our smart connections with the flexibility ofthe pluggable function.

PI-Spring Pluggable

Speed up your projects
Modularity brings assembly flexibility
Pluggable technology brings modularity into the electrical installation
allowing the combination of sub-assemblies and prewired harnesses
that facilitate and considerably accelerate assembly test and factorycommissioning.

3

PI-Spring Pluggable

Better project identification– Circuit identification is improved thanks to the 20% larger marking area
– Pre-mark by hand or with label on our flat marking surface
and start immediately the wiring, before the final markers mounting– Spare markers re-printing in case of modifications.

Pluggable Pluggable

Clear circuit identification

1SNK164014S0201 - Rev. A

Screw clamp Pluggable

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSSubassemblies

1

T
TES

ED

Subassemblies

Subassemblies

1 Serialize plugs harnesses
Instead of one to one wiring, the wires are combined in one
single harness. Production and testing of harnesses can beserialized and outsourced.

2

2 Mounting time reduced by 90%
Reduce the mounting and testing time of the whole
equipment by connecting subassemblies with pluggableterminal blocks and harnesses. Ease the factorycommissioning.

3

Control panel

3 Disconnect for transportation
Easily disconnect the harnesses if needed for convenienttransportation of big equipment.

4 Quickly secure on-site reconnection
Secure oan-site installation: final reconnection is done in few
quick steps and fully secured thanks to error-free coding
system. Facilitate the final commissioning.

3

1SNK164014S0201 - Rev. A

4

PAGE 71

Pluggable technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process
Mounting, wiring, testing… made easy.
Create your own assemblies without tooling:– Easily snap together multiple plugs– Eliminate stock of pre-configured plugs.

Only two plug variants are required to compose harnesses up to 15 poles

Some plugs feature a jumper channel and/or 2 connections
that ease the signal distribution or wiring daisy chaining ofsubassemblies.

Easy signal distribution on plugs

Safety and protection
Eliminate connection errors with coding pegs:– Simply insert the pegs to create a coding sequence.
Secure your wiring against accidental tearing:– Automatic locking function– Lock safely 2 to 8 plugs with only one locking device– Cable clamp secures the wires onto the plug when pulling the plugassembly.
Convenient coding pegs

Cable clamp & locking device

1SNK164014S0201 - Rev. A

3

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSSNK series, terminal blocks
Features and benefits

Faster accessories mounting
Save up to 70% mounting time thanks to:– Screwless jumpers, component plugs, test devices, end stops
and snap-in ground terminal blocks.

Closed jumper location allows great stiffness of the terminal block,
avoid deflection while tightening and optimal jumper guiding.

3

Screwless accessories

Snap-in ground terminal blocks

Closed jumper location for stiffness

Smart accessories
Flexible test solutions from individual insulated test adapter to test
connectors for complete assemblies testing.

Smart plug-in jumpers
Pre-cut poles removable by hand: clean cut.

– Direct plug-in into jumpers channels

Predefined shapes in molding to easily identify connected poles
with a pen.

– 5, 6, 8 mm spacing, mixing various spacing is possible

Insulated up to 1000 V (avoid use of separators).

Plug-in individual test adapter

Plug-in test connector

Pre-cut poles easy removableby handPredefined shape to identify
connected poles

PAGE 73

1SNK164014S0201 - Rev. A– 1000 V rating.

Pluggable technology - SNK series, terminal blocks
Features and benefits

Optimized logistics
Reduce your accessories inventory by up to 50%
SNK PI-Spring, screw and pluggable ranges sharethe same accessories.

Facilitate maintenance operations
Terminal blocks can be individually removed from a terminal
assembly equipped with markers: TE Connectivity markers become
independent after strip mounting. The markers remain on terminal
in any situation.
Markers are interchangable: the smaller marker can fit any bigger block.

3

Maintenance operations facilitated

Reliable in harsh conditions
Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…

Shared accessories for SNK PI-Spring, screw and pluggable ranges

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRoHS

1SNK164014S0201 - Rev. A

CE

1SNK164014S0201 - Rev. A

3

PAGE 75

SNK series, terminal blocks
Pluggable technology - Range overview from 2.5 to 4 mm² – 12 to 10 AWG
PI-Spring pluggable

Pluggable pluggable

PI-Spring pluggable

24Connections

Connections

Connections

3

4

Single deckFeed-throughSingle deckFeed-throughGroundSingle deckFeed-throughGroundSingle deckFeed-throughSingle deckFeed-throughGroundConnections

2

Connections

3

Plugs

Compact plug
Save up to 15%
in height

Jumper plugs
Plugs with 1 or 2 connection& jumper to ease potential
distribution

Reduced plug variants
Only two plugs variants
to create assemblies

Voltage test
Screwdriver entry point
accepts category II probes

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSScrew clamp pluggable

2x2

4

Double deckFeed-throughGroundSingle deckFeed-throughConnections

Connections

3

Locking device
Secure plug andwiring against
accidental pulling

Cable clamp
Secure the wires ontov
the plug when pulling
the plug assembly
1SNK164013S0201

End section
No need of end section
between 2.5 and 4 mm2
terminal blocks

Convenient coding pegs
Guarantee error freeplugs insertion

PAGE 77

SNK series, terminal blocks
Pluggable technology

PI-Spring Pluggable

Singledeck
Feed-throughGroundFeed-throughGroundSection
12 AWG
10 AWG

ZD2.5-11

ZD2.5-22

ZD2.5-22-PE

ZDK2.5-11

ZDK2.5-21

ZDK2.5-22

ZDK2.5-11-PE

ZDK2.5-22-PE

ZDK4-22

Doubledeck
Feed-throughFeed-through+ groundGroundZDK2.5-D2-PE

ZDK2.5-D1-PE

Section
2.5 mm²

12 AWG

4 mm²

10 AWGZDK2.5-D2

PI-Springfemaleplugs

ZDK2.5-D1

ClosedClosedClosedClosedClosedClosedSection
2.5 mm²

12 AWG

CDK2.5

CDK2.5-E

4 mm²

10 AWG

CDK4

CDK4-E

CDK2.5-J

CDK2.5-J-E CDK2.5-2P-J CDK2.5-2P-J-E CDK2.5-PE

CDK2.5-PE-E

CDK2.5-J-PE

CDK2.5-J-PE-E CDK2.5-2P-J-PE CDK2.5-2P-J-PE

Screw clamp Pluggable

Screw
clamp
femaleplugs

Singledeck
Feed-throughSection
4 mm²

ClosedSection
10 AWG

clamp -

ZDS4-22
ZDS4-22-R1

Channels for jumpering or testing -4 mm²

test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Blown-fuse indicator -male pluggable clamp -10 AWG

CDS4
CDS4-R1

female pluggable clamp

CDS4-E

1SNK164018S0201

3

2.5 mm²
4 mm²

3

PB-171

PI-Spring Pluggable

PAGE 79

ZD2.5-11 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164014V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through2 connections

Grey

Type

Part Number

Pkg Weightqty (1 pce) g

ZD2.5-11

1SNK805016R0000

50

Main technical data

ZD2.5-11

54.4 2.13"

61.6 2.43"

69.1 2.72"

46.1 1.81"

53.6 2.09"

3

5.66

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inRated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

Tool (for flexible

conductor without
ferrule)Ø 3.5 mm
Ø 0.138 in

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
24.2 0.94"
CE

CB

USR CNR

RoHS

CSA

EAC

BV

5.2 mm 0.205 in spacing

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed
CDK2.5Color
1 pole1 poleGrey

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.

CDK2.5-E

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
1.5 mm
0.059 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-11
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R2
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805915R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900106R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

5.30
1.49
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164020S0201

1

ZD2.5-22 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164015V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through

GreyPart Number

Pkg Weightqty (1 pce) g

ZD2.5-22

1SNK805017R0000

50

Main technical data

47.5 1.85"

5.2 mm 0.205 in spacing

61.6 2.43"

101.9 3.98"

69.1 2.72"

46.1 1.81"

53.6 2.09"

ZD2.5-22

4 connections

Type

12.00

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)3

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

Female plugs
Female plugs withoutouter nubs - Closed

CDK2.5-E

Color
1 pole1 poleGrey

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1ED2.5-22
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805917R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

5.30
3.64
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 81

1SNK164021S0201

1

ZD2.5-22-PE PI-Spring pluggable terminal blocks
Ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164016V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color
4 connections

GroundGreen-yellow

Part Number

Pkg Weightqty (1 pce) g

ZD2.5-22-PE

1SNK805156R0000

50

Main technical data

69.1 2.72"

108.4 4.25"

3

61.6 2.43"

46.1 1.81"

53.6 2.09"

ZD2.5-22-PE

Type

14.80

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 147.5 1.85"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

CDK2.5-PE CDK2.5-PE-E

Color
1 pole1 poleTypePart Number

Pkg Weightqty (1 pce) g

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey
Dark grey

BAZ1
ED2.5-22
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805917R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
20
20
20
10
10
10
22
20
1960
10

Green-yellow

2.80
2.88

15 poles max.

Accessories

3

5

7

Description

2

4

6

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Test connectors

6
7

Coding pegs
Terminal block
markers

5.2 mm0.205 in
2.0 mm
0.079 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Blank marker
Universal wire markers holder

Dark grey
Dark grey
White

Grey

5.30
3.64
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164022S0201

1

ZDK2.5-11 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164017V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through2 connections

Grey
Blue

Type

Part Number

Pkg Weightqty (1 pce) g

ZDK2.5-11
ZDK2.5-11-BL

1SNK805015R0000
1SNK805025R0000

50
50

Main technical data
ZDK2.5-11

58.6 2.31"

66.1 2.60"

43 1.69"

50.5 1.98"

49.6 1.93"

23.3 0.91"

7.00
7.00

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)3

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

CDK2.5-E

CDK2.5-BL CDK2.5-BL-E

Female plugs
Female plugs withoutouter nubs - Closed
Female plugs
Female plugs withoutouter nubs - Closed

Color

Type

Part Number

Pkg Weightqty (1 pce) g

1 pole1 poleGrey

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

1 pole1 poleBlue

CDK2.5-BL
CDK2.5-BL-E

1SNK805742R0000
1SNK805743R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
1.5 mm
0.059 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-11
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R2
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805915R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900106R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

5.30
1.49
1.30
2.00
2.70
3.50
7.10
36.00
2.80
3.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 83

1SNK164023S0201

1

ZDK2.5-21 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164020V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-through3 connections

Grey

Type

Part Number

Pkg Weightqty(1 pce) g

ZDK2.5-21

1SNK805014R0000

50

7.47

Main technical data
ZDK2.5-21

65.1 2.56"

23.3 0.91"

5.2 mm 0.205 in spacing

66.1 2.60"
58.6 2.31"

50.5 1.98"
43 1.69"

3

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A1000 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CECB

USR CNR

RoHS

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed
CDK2.5Color
1 pole1 poleGrey

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.

CDK2.5-E

1

2

3

4

5

6

7

8

1
2
3

4
5
6
7
8
9

9

Description

Color

Type

Part Number

Pkg
qty

Weight(1 pce) g

5.2 mm0.205 in
1.5 mm
0.059 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
0.118 inCircuit separators 3 mm
For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-21
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805914R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
22
20
1960
10

5.30
1.90
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164025S0201

Accessories

ZDK2.5-22 PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
Description

2.5 mm²

1SNK162093V0014

12 AWG–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible for convenient
testing.

Ordering details
Description
Feed-throughFeed-through

ZDK2.5-22

Color

Type

4 connections
4 connections

Grey
Blue

ZDK2.5-22
ZDK2.5-22-BL

1SNK805010R0000
1SNK805020R0000

UL - CSARail

Main technical data

66.1 2.60"
58.6 2.31"

50.5 1.99"
43 1.69"
47.5 1.87"

5.2 mm 0.205 in spacing

Pkg

Weightqty(1 pce) g

50
50

9.60
9.60

Mounting instructions

Connecting capacity
89.3 3.52"

Part numberIEC

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

24 A / 2.5 mm²
300 A

22 A / 12 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

600 V

TH 35-7.5,
TH 35-15
11 mm
0.433 in3

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDK2.5

CDK2.5-E

1 poleType
GreyPart number

Pkg

Weightqty(1 pce) g

2.80
2.80

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

Type

Part number

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
10
10
10
1960
22
20
10

5.30
3.15
1.30
2.00
2.70
3.50
7.10
36.00
2.80
6.40
1.70
2.40
5.20
5.20
3.57
0.23
9.00
10.00
0.20

15 poles max.

1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

5.2 mm0.205 in
2.2 mm0.087 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAZ1
1SNK900002R0000
EDK2.5-22
1SNK805910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
Technical data valid for copper conductors only.

PAGE 85

1SNK164001S0201

Accessories

ZDK4-22 PI-Spring pluggable terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²

1SNK162094V0014

10 AWG–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5-R1 + ES-TC6) withstanding 10 000 operations are compatible
for convenient testing.

Ordering details
Description
Feed-through

Color

Type

4 connections

ZDK4-22

1SNK806010R0000

IEC

UL - CSA

Rail
Wire stripping
lengthGrey

Main technical data

ZDK4-2267.2 2.65"
59.7 2.35"

50.5 1.99"
43 1.69"3

50.3 1.98"

6 mm 0.236 in spacing

Pkg

Weightqty(1 pce) g

50

14.30

Mounting instructions

Connecting capacity
93.8 3.69"

Part Number

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

30 A / 4 mm²
480 A

30 A / 10 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

600 V

TH 35-7.5,
TH 35-15
12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDK4

CDK4-E

1 poleType
GreyPart Number

Pkg

Weightqty(1 pce) g

3.80
4.50

CDK4
CDK4-E

1SNK806712R0000
1SNK806713R0000

50
50

Type

Part Number

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
10
10
10
1680
22
20
10

5.30
3.15
1.30
2.10
2.90
3.60
7.40
38.10
2.80
6.40
1.70
2.40
5.20
0.80
3.57
0.27
10.00
11.00
0.20

15 poles max.

1

Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

5.2 mm0.205 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
5 Circuit separators 3 mm
0.118 in6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
End module, 5.2 mm 0.205 in
8 Spacers
0.8 mm
0.031 in9 Coding pegs
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAZ1
1SNK900002R0000
EDK2.5-22
1SNK805910R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164002S0201

Accessories

ZDK2.5-11-PE PI-Spring pluggable terminal blocks
Ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164019V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color
2 connections

GroundGreen-yellow

TypePart Number

Pkg Weightqty (1 pce) g

ZDK2.5-11-PE

1SNK805150R0000

50

Main technical data
ZDK2.5-11-PE

58.6 2.31"

66.1 2.60"

43 1.69"

50.5 1.98"

56.1 2.20"

9.62

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

3

24.2 0.94"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - ClosedColor
1 pole1 poleTypePart Number

Pkg Weightqty (1 pce) g

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey
Dark grey

BAZ1
EDK2.5-11
CS-R2
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805915R0000
1SNK900106R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
20
20
20
10
10
10
22
20
1960
10

Green-yellow

2.80
2.88

15 poles max.

CDK2.5-PE CDK2.5-PE-E

Accessories

3

5

7

Description

2

4

6

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Test connectors

6
7

Coding pegs
Terminal block
markers

5.2 mm0.205 in
1.5 mm
0.059 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Blank marker
Universal wire markers holder

Dark grey
Dark grey
White

Grey

5.30
1.49
3.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

1SNK164024S0201

1

Technical data valid for copper conductors only.

PAGE 87ZDK2.5-22-PE PI-Spring pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164022V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Color

Type

Part Number

Pkg Weightqty (1 pce) g

Green-yellow

ZDK2.5-22-PE

1SNK805152R0000

50

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Description
4 connections

Ground14.05

ZDK2.5-22-PE

Main technical data

47.5 1.85"

66.1 2.60"

58.6 2.31"

3

43 1.69"

50.5 1.98"

94.7 3.70"

Mounting instructions

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey
Dark grey

BAZ1
EDK2.5-22
CS-R3
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805910R0000
1SNK900107R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
20
20
20
10
10
10
22
20
1960
10

Color
1 pole1 poleGreen-yellow

2.80
2.88

15 poles max.

CDK2.5-PE CDK2.5-PE-E

Accessories

3

5

7

Description

2

4

6

1
2
3
4

End stops
End sections
Circuit separators
Test adapters

5

Test connectors

6
7

Coding pegs
Terminal block
markers

5.2 mm0.205 in
2.2 mm0.087 in
3 mm
0.118 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Blank marker
Universal wire markers holder

Dark grey
Dark grey
White

Grey

5.30
3.15
6.40
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164026S0201

1

ZDK2.5-D2 PI-Spring pluggable terminal blocks
Double deck feed-through 2 circuits - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164023V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-throughdouble deck 4 connections

Grey
Blue

Type

Part Number

Pkg Weightqty (1 pce) g

ZDK2.5-D2
ZDK2.5-D2-BL

1SNK805213R0000
1SNK805223R0000

50
50

Main technical data
ZDK2.5-D2

85.2 3.35"

77.7 3.06"

69.6 2.72"

62.1 2.44"

81.5 3.19"

40.6 1.57"

5.2 mm 0.205 in spacing

11.89
11.89

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A
800 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)3

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

CDK2.5-E

CDK2.5-BL CDK2.5-BL-E

Female plugs
Female plugs withoutouter nubs - Closed
Female plugs
Female plugs withoutouter nubs - Closed

Color

Type

Part Number

Pkg Weightqty (1 pce) g

1 pole1 poleGrey

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

1 pole1 poleBlue

CDK2.5-BL
CDK2.5-BL-E

1SNK805742R0000
1SNK805743R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-D
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805913R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
White

Grey

5.30
3.88
1.30
2.00
2.70
3.50
7.10
36.00
2.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

PAGE 89

1SNK164029S0201

1

ZDK2.5-D1 PI-Spring pluggable terminal blocks
Double deck feed-through 1 circuit - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164025V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Feed-throughdouble deck 4 connections

Grey

Type

Part Number

Pkg Weightqty (1 pce) g

ZDK2.5-D1

1SNK805214R0000

50

Main technical data
ZDK2.5-D1

81.5 3.19"

85.2 3.35"

77.7 3.06"

69.6 2.72"

62.1 2.44"

3

12.46

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A
800 V
8000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

40.6 1.57"

5.2 mm 0.205 in spacing

CE

CB

USR CNR

RoHS

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

1 pole1 pole

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Grey

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

15 poles max.
CDK2.5

CDK2.5-E

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-D
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805913R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
White

Grey

5.30
3.88
1.30
2.00
2.70
3.50
7.10
36.00
2.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164027S0201

1

ZDK2.5-D2-PE PI-Spring pluggable terminal blocks
Double deck feed-through + ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164027V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Grey, Greenyellow

ZDK2.5-D2-PE

1SNK805212R0000

50

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm²
300 A
800 V
8000 V
IP20

Feed-through +grounddouble deck 4 connections

Main technical data
ZDK2.5-D2-PE

85.2 3.35"

77.7 3.06"

69.6 2.72"

62.1 2.44"

88.5 3.46"

40.6 1.57"

5.2 mm 0.205 in spacing

16.13

Mounting instructions

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)3

20 A / 12 AWG
396 A
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

CDK2.5

CDK2.5-E

CDK2.5-PE CDK2.5-PE-E

Female plugs
Female plugs withoutouter nubs - Closed
Female plugs
Female plugs withoutouter nubs - ClosedColor
1 pole1 poleGrey

1 pole1 poleGreen-yellow

TypePart Number

Pkg Weightqty (1 pce) g

CDK2.5
CDK2.5-E

1SNK805712R0000
1SNK805713R0000

50
50

2.80
2.88

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

2.80
2.88

15 poles max.

Accessories
2

3

4

5

6

7

8

1
2
3

4
5
6
7
8

Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

5.2 mm0.205 in
2.0 mm
0.079 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
Test adapters
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
Test connectors
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank card
markers
Blank marker
Universal wire markers holder

Dark grey
Dark grey
OrangeBAZ1
EDK2.5-D
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50JB85-3TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PA
MG-CPM 13 41790
UMH

1SNK900002R0000
1SNK805913R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900603R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNB041790R0512
1SNK900611R0000

50
20
50
50
50
50
30
10
10
20
20
10
10
10
22
20
1960
10

End stops
End sections
Jumper bars

OrangeDark grey
Dark grey
Dark grey
White

Grey

5.30
3.88
1.30
2.00
2.70
3.50
7.10
36.00
2.80
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 91

1SNK164030S0201

1

ZDK2.5-D1-PE PI-Spring pluggable terminal blocks
Double deck ground - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164026V0014

12 AWG

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation,
easily connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection
testing is eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible forconvenient testing.

Ordering details
Description

Color
double deck 4 connections

GroundGreen-yellow

TypePart Number

Pkg Weightqty (1 pce) g

ZDK2.5-D1-PE

1SNK805250R0000

50

Main technical data
ZDK2.5-D1-PE

88.5 3.46"

Mounting instructions

Connecting capacity

IEC

UL - CSARail

TH 35-7.5,
TH 35-15

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

26 ... 14 AWG
26 ... 14 AWG
conductor without
ferrule)85.2 3.35"

77.7 3.06"

69.6 2.72"

5.2 mm 0.205 in spacing

62.1 2.44"

340.6 1.57"

16.80

Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG
396 A

Protection

IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description
Female plugs
Female plugs withoutouter nubs - Closed

1 pole1 pole

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Green-yellow

CDK2.5-PE
CDK2.5-PE-E

1SNK805750R0000
1SNK805753R0000

50
50

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Dark grey
Dark grey
Dark grey

BAZ1
EDK2.5-D
TP2
TP4
TC5
TC5-R1
COP-ZD
MC512
MC512PAUMH

1SNK900002R0000
1SNK805913R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900636R0000
1SNK140000R0000
1SNK149999R0000
1SNK900611R0000

50
20
20
20
10
10
10
22
20
10

2.80
2.88

15 poles max.

CDK2.5-PE CDK2.5-PE-E

Accessories
1

3

5

Description

2

4

6

1
2
3

End stops
End sections
Test adapters

4

Test connectors

5
6

Coding pegs
Terminal block
markers

5.2 mm0.205 in
2.0 mm
0.079 in
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Blank card
Universal wire markers holder

Dark grey
Dark grey
White
Grey

5.30
3.88
1.70
2.40
5.20
5.20
3.57
9.00
10.00
0.20

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164028S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.

CDK2.5 PI-Spring female plugs
Female plug - 5.2 mm 0.205 in spacing
Description

2.5 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDK2.5

1SNK160292V0014

1SNK160291V0014

12 AWG

CDK2.5-E

Ordering details
Description

Color

Female plugs
Female plugs without outer nubs - Closed

Type

Grey
Blue
Green-Yellow
Grey
Blue
Green-Yellow

CDK2.5
CDK2.5-BL
CDK2.5-PE
CDK2.5-E
CDK2.5-BL-E
CDK2.5-PE-E

1SNK805712R0000
1SNK805742R0000
1SNK805750R0000
1SNK805713R0000
1SNK805743R0000
1SNK805753R0000

IEC

UL - CSARail

Main technical data
19.1 0.75"

21.1 0.83"

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.2 ... 4 mm²
26 ... 12 AWG
0.22 ... 2.5 mm²0.22 ... 2.5 mm² 26 ... 14 AWG
0.22 ... 2.5 mm² 26 ... 14 AWG

Wire stripping
length2 conductors
per clamp

Flexible with twin ferrule

0.22 ... 0.5 mm² 26 ... 20 AWG

Tool (for flexible

36.2 1.43"

Pkg

Weightqty(1 pce) g

50
50
50
50
50
50

2.80
2.80
2.80
2.80
2.80
2.80

Mounting instructions

Connecting capacity

5.2 mm 0.205 in spacing

Part number

conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

24 A / 2.5 mm²
300 A

22 A / 12 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 V
IP20

600 V

11 mm
0.433 in3

Flat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41790 1SNB041790R0512
MG-CPMFA 43196 1SNB043196R0012
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1960
350
22
20
10

0.7
1.04
0.23
2.56
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK164005S0201

3

Locking devices
Cable clamp
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 93

CDK2.5-J PI-Spring female plugs
Female plug - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164001V0014

1SNK164000V0014

12 AWG

Description–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs
for optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in caseof needed modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.
Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Female plugs

Grey
Blue
Green-yellow
Grey
Blue
Green-yellow

CDK2.5-J
CDK2.5-J-BL
CDK2.5-J-PE
CDK2.5-J-E
CDK2.5-J-BL-E
CDK2.5-J-PE-E

1SNK805738R0000
1SNK805744R0000
1SNK805748R0000
1SNK805739R0000
1SNK805745R0000
1SNK805749R0000

50
50
50
50
50
50

Connecting capacity

IEC

UL - CSA

Rail

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A
800 V
8000 V
IP20

Female plugs without outer nubs - Closed
CDK2.5-J

CDK2.5-J-E

Main technical data
23.8 0.91"

19.1 0.75"

5.2 mm 0.205 in spacing

42.9 1.65"

27.8 1.06"

3

4.08
4.08
4.08
4.34
4.34
4.34

Mounting instructions

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
Description

2

3

4

5

6

1

Jumper bars

2

Test adapters

3

Test connectors

4
5
6

Locking devices
Strain Relief
Terminal block
markers

2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
9.4 mm 0.370 in spacing
Blank card
Blank strip label
Blank marker
Universal wire markers holder

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Orange

JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50TP2
TP4
TC5
TC5-R1
VR-ZD
PT-ZD
MC512
MC512PA
MG-CPMFA 43196
MG-CPM 13 41790
UMH

1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900637R0000
1SNK900660R0000
1SNK140000R0000
1SNK149999R0000
1SNB043196R0012
1SNB041790R0512
1SNK900611R0000

50
50
50
50
30
10
20
20
10
10
50
50
22
20
400
1960
10

Dark grey
Dark greyBlack
Dark grey
White

Grey

1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.7
1.04
9.00
10.00
2.562
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164031S0201

1

CDK2.5-2P-J PI-Spring female plugs
Female plug - 5.2 mm 0.205 in spacing
2.5 mm²

1SNK164002V0014

1SNK164003V0014

12 AWG

CDK2.5-2P-J

CDK2.5-2P-J-E

35.5 1.38"

Description–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs
for optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in caseof needed modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.
Description

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Female plugs

Grey
Blue
Green-yellow
Grey
Blue
Green-yellow

CDK2.5-2P-J
CDK2.5-2P-J-BL
CDK2.5-2P-J-PE
CDK2.5-2P-J-E
CDK2.5-2P-J-BL-E
CDK2.5-2P-J-PE-E

1SNK805740R0000
1SNK805746R0000
1SNK805751R0000
1SNK805741R0000
1SNK805747R0000
1SNK805752R0000

50
50
50
50
50
50

Female plugs without outer nubs - Closed

29.8 1.14"
19.1 0.75"

5.2 mm 0.205 in spacing

44.9 1.73"

Main technical data

5.37
5.37
5.37
5.74
5.74
5.74

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

1 conductor per Rigid: Solid/Stranded
Flexible without ferrule
clamp
Flexible with non insulated ferrule
Flexible with insulated ferrule
Flexible with twin ferrule
2 conductors
per clamp

0.2 ... 4 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 0.5 mm²

26 ... 12 AWG

Wire stripping
length11 mm
0.433 inTool (for flexible

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

24 A / 2.5 mm²
300 A
500 V
6000 V
IP20

26 ... 14 AWG
26 ... 14 AWG
26 ... 20 AWG

conductor without
ferrule)3

20 A / 12 AWG
600 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

1

Description

2

3

4

5

6

1

Jumper bars

2

Test adapters

3

Test connectors

4
5
6

Locking devices
Strain Relief
Terminal block
markers

2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
9.4 mm 0.370 in spacing
Blank card
Blank strip label
Blank marker
Universal wire markers holder

Color

Type

Part Number

Pkg Weightqty (1 pce) g

Orange

JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50TP2
TP4
TC5
TC5-R1
VR-ZD
PT-ZD
MC512
MC512PA
MG-CPMFA 43196
MG-CPM 13 41790
UMH

1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK900203R0000
1SNK900205R0000
1SNK900200R0000
1SNK900201R0000
1SNK900637R0000
1SNK900660R0000
1SNK140000R0000
1SNK149999R0000
1SNB043196R0012
1SNB041790R0512
1SNK900611R0000

50
50
50
50
30
10
20
20
10
10
50
50
22
20
400
1960
10

Dark grey
Dark greyBlack
Dark grey
White

Grey

1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
0.7
1.04
9.00
10.00
2.562
0.236
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of
the catalog.
Technical data valid for copper conductors only.

PAGE 95

1SNK164032S0201

Accessories

CDK4 PI-Spring female plugs
Female plug - 6 mm 0.236 in spacing
Description

4 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDK4

1SNK160294V0014

1SNK160293V0014

10 AWG

CDK4-E

Ordering details
Description

Color

21.2 0.83"

36.3 1.43"

3

6 mm 0.236 in spacing

Part Number

CDK4
CDK4-E

1SNK806712R0000
1SNK806713R0000

IEC

UL - CSA

Rail
Wire stripping
lengthFemale plugs
Female plugs without outer nubs - Closed

Grey

Main technical data

Pkg

Weightqty(1 pce) g

50
50

3.80
4.50

Mounting instructions

Connecting capacity

20.6 0.81"

Type

1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule

0.5 ... 6 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²

26 ... 10 AWG

2 conductors
per clamp

Flexible with twin ferrule

0.5 ... 1 mm²

26 ... 18 AWG

26 ... 12 AWG
26 ... 12 AWG

Tool (for flexible
conductor without
ferrule)Rated current / Rated cross section
Rated short-time withstand current (1s)

30 A / 4 mm²
480 A

30 A / 10 AWG

Rated voltage
Impulse withstand voltage
Protection

1000 V
8000 VIP20600 V

12.5 mm0.492 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

3

Locking devices
Cable Clamp
Terminal block
markersColor
9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part Number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41791 1SNB041791R0612
MG-CPMFA 43196 1SNB043196R0012
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1680
350
22
20
10

0.7
1.04
0.27
2.56
10.00
11.00
0.20

1SNK164006S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

3

PB-189Screw clamp Pluggable

PAGE 97

ZDS4-22 Screw clamp pluggable terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
Description

4 mm²–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5) withstanding 10 000 operations are compatible for convenient
testing.
1SNK161137V0014

10 AWG

Ordering details
Description
Feed-through

Color

Type

4 connections

Grey

ZDS4-22Main technical data
ZDS4-2256.4 2.22"
48.9 1.93"
73 2.87"
65.5 2.58"

3

48.3 1.90"

5.2 mm 0.205 in spacing

1SNK805013R0000

Pkg

Weightqty(1 pce) g

50

10.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp
80.3 3.16"

Part Number

24 … 10 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
28 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDS4

CDS4-E

1 poleType
GreyPart Number

Pkg

Weightqty(1 pce) g

3.90
4.10

CDS4
CDS4-E

1SNK805714R0000
1SNK805715R0000

50
50

Type

Part Number

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
20
20
20
10
10
10
1960
22
20
10

14.00
1.85
1.30
2.00
2.70
3.50
7.10
36.00
6.40
1.70
2.40
5.20
5.20
3.57
0.23
9.00
10.00
0.20

15 poles max.

1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

Color

10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
Coding pegs
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAM4
1SNK900001R0000
EDS4-22
1SNK805911R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164003S0201

Accessories

CDS4 Screw clamp female plugs
Female plug - 5.2 mm 0.205 in spacing
Description

4 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDS4

1SNK160296V0014

1SNK160295V0014

10 AWG

CDS4-E

Ordering details
Description

Color

Female plugs
Female plugs without outer nubs - Closed

Grey

24.3 0.96"

39.4 1.55"

5.2 mm 0.205 in spacing

Part Number

CDS4
CDS4-E

1SNK805714R0000
1SNK805715R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

3.90
4.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
length10.5 mm0.413 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp

22.4 0.88"

Type

24 … 10 AWG
24 ... 12 AWG
24 ... 16 AWG
24 ... 16 AWG
28 A / 10 AWG

3NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part Number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41790 1SNB041790R0512
MG-CPMFA 43196 1SNB043196R0012
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1960
350
22
20
10

0.7
1.04
0.23
2.56
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK164007S0201

3

Locking devices
Cable Clamp
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 99

ZDS4-22-R1 Screw clamp pluggable terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses,
time saving plug and play assembly, reduced transportation panels preparation and final installation, easily
connect sub-assemblies together,–– Simplify and secure your installation: in site faulty connection errors are eliminated, prior connection testingis eased and reliable, test connectors (TC5-R1 + ES-TC6) withstanding 10 000 operations are compatible
for convenient testing.
1SNK161138V0014

10 AWG

Ordering details
Description
Feed-through

Color

Type

4 connections

Grey

ZDS4-22-R1

Main technical data
ZDS4-22-R1

73 2.87"
65.5 2.58"

56.4 2.22"
48.9 1.93"

3

48.3 1.90"

6 mm 0.236 in spacing

1SNK806013R0000

Pkg

Weightqty(1 pce) g

40

12.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp
80.3 3.16"

Part Number

24 … 10 AWG
24 … 10 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
28 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Female plugs
Description

Color

Female plugs
Female plugs without outer nubs Closed
CDS4-R1

CDS4-E

1 poleType
GreyPart Number

Pkg

Weightqty(1 pce) g

4.10
4.10

CDS4-R1
CDS4-E

1SNK806714R0000
1SNK805715R0000

50
50

Type

Part Number

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
20
20
20
10
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
38.10
6.40
1.70
2.40
5.20
0.80
3.57
0.27
10.00
11.00
0.20

15 poles max.

1

Description

2
1
2

3

4

5

6

7

8

3
4
5
6
7
8

Color

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inCoding pegs
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
Dark grey
White

Grey

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
CS-R3
1SNK900107R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
COP-ZD
1SNK900636R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK164004S0201

Accessories

CDS4-R1 Screw clamp female plugs
Female plug - 6 mm 0.236 in spacing
Description

4 mm²–– Create your own female plug assemblies without any special tools, easily snap together multiple plugs for
optimal ergonomics and quick assembly,–– Increase your flexibility: eliminate stock of pre-configured female plugs, easily add an extra plug in case ofneeded modification,–– Reduce your stock of unitary plugs up to 30%: only two plug variants are required to compose your own
subsets of plugs from 2 to 15 poles.

CDS4-R1

1SNK160296V0014

1SNK160297V0014

10 AWG

CDS4-E

Ordering details
Description

Color

Female plugs
Female plugs without outer nubs - Closed

Grey

24.3 0.96"

39.4 1.55"

6 mm 0.236 in spacing

Part Number

CDS4-R1
CDS4-E

1SNK806714R0000
1SNK805715R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

4.10
4.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²0.22 … 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
length10.5 mm0.413 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp

22.4 0.88"

Type

24 … 10 AWG
24 … 10 AWG
24 ... 16 AWG
24 ... 16 AWG
28 A / 10 AWG

3NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

Mounting instructions
15 poles max.

Accessories
1

Description

2
1
2
3

9.4 mm 0.370 in spacing
9.4 mm 0.370 in spacing
Blank marker
Blank strip label
Blank card
Universal wire markers holder

Black
Dark grey
White

Grey

Type

Part Number

VR-ZD
1SNK900637R0000
PT-ZD
1SNK900660R0000
MG-CPM 13 41791 1SNB041791R0612
MG-CPMFA 43196 1SNB043196R0012
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
1680
350
22
20
10

0.7
1.04
0.27
2.56
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK164008S0201

3

Locking devices
Cable Clamp
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 101

4

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
ADO System® IDC and pluggable technologies

Technologies presentation				
104
Overview					106Feed-through
1.5 mm²
1.82 mm²2.61 mm²
1.5 mm²
4.32 mm²

D1.5/5.ADO.NF			110D1.5/6.ADO.NF				111D2.5/8.ADO.NF			112D2.5/8.ADO.NF1			113D4/8.ADO.NF
			114

Disconnect with plug1.82 mm²
D1.5/6.S.ADO.NF 				
1152.61 mm²D2.5/8.S.ADO.NF
			116
Double deck
1.82 mm²

D1.5/6.D2.ADO.NF				
117

Component holder
1.82 mm²

D1.5/6.ADO.D2.NF

Pluggable
1.82 mm²
1.5 mm²
1.82 mm²2.61 mm²
4.32 mm²

Female plugs
1.82 mm²

D1.5/7.ADO-CPE.NF
D2.5/7.ADO-CPE.NF1
D1.5/7.2ADO-CPE.NF
D2.5/7.ADO-CPE.NF
D2.5/7.2ADO-CPE.NF
D4/7.ADO-CPE.NF
D4/7.2ADO-CPE.NF
D2.5/7.2CPE
D2.5/7.2CPE.CPE

			
118

1x ADO system - 1x pluggable		
1x ADO system - 1x pluggable		
2x ADO system - 1x pluggable		
1x ADO system - 1x pluggable		
2x ADO system - 1x pluggable		
1x ADO system - 1x pluggable		
2x ADO system - 1x pluggable		
1x pluggable - 1x pluggable		
1x pluggable - 1x pluggable		

4.32 mm²

L 266 200 15
L 266 200 25
L 277 200 15
L 267 200 15
L 267 200 25
L 276 200 15

4 and 5 poles			

128
129
130
131
132
133

Male plugs
1.82 mm²2.61 mm²

L 366 200 45
L 367 200 45		2 to 10 poles			134

2 to 10 poles 		135

2 to 10 poles-with brackets		
2 to 6 poles			
2 to 10 poles			
2 to 10 poles			

Summary_4

2.61 mm²

2 to 10 poles			

4

119
120
121
122
123
124
125
126
127

PAGE 103Railway applications, terminal blocks
ADO System® IDC and pluggable technologies

The fastest connection
technology for rolling stock
The ADO system ® technology based on insulation displacement(IDC) technology offers significant productivity savings as well
as secure and reliable connection in case of vibration andshock.
Combined with the pluggable technology, it increases the
productivity thanks to pre-produced plugs harnesses.

CE

RoHS

EAC

4

Reliable in harsh conditions
Continuous operation guaranteed for rolling stock–– Environmental tests: aging, corrosion, flammability, toxicity(I2F2, V0, HL3 R22)–– Mechanical tests: vibration and shock.

Cost effective solution

80% wiring time reduced compared to traditional technologies–– Asymmetrical design avoid mounting and wiring errors.
–– Zero-retightening with our technologies.

Improve installation efficiency

Connection process simplified and secured

1SNC167090S0201–– Tool locked during the connection process–– Optimized wiring with pluggable technology–– Up to 2 conductors per ADO clamp.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSFeatures

Tool not released until
the connection to becompleted

4

Contact lips:
allows the electricalcontact with a permanent
cable contact pressure

Cone entry shape:
allows the insulation cuttingFirst wire maintained in theclamp during the second wire
cabling process

1SNC167090S0201

Corrosion proof: contact
points are wrapped by
the insulation

ADO System® jaw:
"C shape" spring

PAGE 105

Railway applications, terminal blocks
ADO System® IDC and pluggable technologies
Range overview from 1.5 mm² up to 4 mm² - 16 AWG up to 12 AWG

Feed-throughRed = 1.5 mm² / 16 AWG
Blue = 2.5 mm² / 14 AWG
Yellow = 4 mm² / 12 AWG

4Specific color marking
Easy identification of the wire size

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSConnection of up to 2 wires
Save space by connecting
up to 2 conductors in 1 connectionComponent holder
1.5 mm² / 16 AWG
Disconnect with plug
1.5 and 2.5 mm²
16 and 14 AWG

Pluggable
From 1.5 to 4 mm²
From 16 to 12 AWG

4

Double jumper channel
Plug-in insulated
jumpers

EN 50306 compatibility
The clamps are compatible
with thin insulated conductors

1SNC167091S0201

Locking lever
Secure against
accidental wire pulling

PAGE 107

Railway applications, terminal blocks
ADO System® IDC and pluggable technologies

Feed-throughSection
1.5 mm²
1.82 mm²2.61 mm²
4.32 mm²

D1.5/5.ADO.NF

D2.5/8.ADO.NF1
D1.5/6.ADO.NF
D2.5/8.ADO.NF
D4/8.ADO.NF

4Pluggable

Feed-through: 1 ADO - 1 pluggable

Section
1.5 mm²
1.82 mm²2.61 mm²
4.32 mm²D2.5/7.ADO-CPE.NF1
D1.5/7.ADO-CPE.NF
D2.5/7.ADO-CPE.NF
D4/7.ADO-CPE.NF

Female plugs for pluggable terminal blocks
Section
1.5 mm²
1.82 mm²2.61 mm²
4.32 mm²

Clamp -

L 277 200 15
L 266 200 15

L 266 200 25
L 267 200 15

L 267 200 25
L 276 200 15

Channels for jumpering or testing -Test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Blown-fuse indicatorDouble deck

Disconnect with plug

D1.5/6.D2.ADO.NF

Component holder

D1.5/6.S.ADO.NF

D1.5/6.ADO.D2.NF
D2.5/8.S.ADO.NF

4Feed-through: 2 ADO - 1 pluggable

Feed-through: 2 pluggables

D1.5/7.2ADO-CPE.NF
D2.5/7.2ADO-CPE.NF
D4/7.2ADO-CPE.NF

D2.5/7.2CPE
D2.5/7.2CPE
D2.5/7.2CPE
D2.5/7.2CPE

D2.5/7.CPE.CPE
D2.5/7.CPE.CPE
D2.5/7.CPE.CPE
D2.5/7.CPE.CPE

Male plugs

L 366 200 45

1SNC167092S0201

L 367 200 45

PAGE 109

D1.5/5.ADO.NF IDC terminal blocks
Feed-through - ADO System® - 5 mm 0.197 in spacing
1.5 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

1SNC167094V0014

Ordering details
Description

Color

Feed-through

TypePart Numbers

D1.5/5.ADO.NF

Beige

Main technical data
Connecting capacity
ADO

D1.5/5.ADO.NF

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

Weight(1 pce) g

50

5.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400315R0100

Pkg
qty

NF F 63-296
NF F 63-826

0.6 … 1.34 mm²IEC17.5 A
180 A
1000 V
8000 V
IP20

RoHS

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

EAC

4

5 mm 0.197 in spacing

Accessories
1

Description

2
1
2
3

3

4

5

6

7

6
7

10 mm
0.394 in
3 mm
0.118 in
2 poles
24 A (IEC)3 poles
24 A (IEC)4 poles
24 A (IEC)
5 poles
24 A (IEC)
10 poles24 A (IEC)
Circuit separators 0 mm
0 in
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
Test plugs
DIA 2 mm 0.079 in
Shield connectors

8

Tools

9

Terminal block
markers

4
5

End stops
End sections
Jumper bars

Semi automatic tool
Hand tool
Blank card

Beige
Beige

Grey

Black

White

Type
BAM2
FEMAD3
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
SCAD5
AL2
AL3
FC2
CBM5
CBM8
OUPAD
OUMAD
RC510
RC55

Part Numbers
1SNA296351R0000
1SNA399802R0500
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA199551R2000
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA178745R1400
1SNA178746R1500
1SNA178944R0400
1SNA179466R0600
1SNA231000R0700
1SNA230000R1200

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
50
50
100
50
50
1
1
10
10

12.00
2.50
3.30
5.00
6.70
8.40
16.90
0.30
0.90
1.20
2.00
1
1
205.00
29.00
5.20
2.90

1SNC167072S0201

9

8

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD1.5/6.ADO.NF IDC terminal blocks
Feed-through - ADO System® - 6 mm 0.236 in spacing
1.82 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

1SNC167122V0014

Ordering details
Description

Color

Feed-through

TypePart Numbers

D1.5/6.ADO.NF

Beige

Main technical data
Connecting capacity
ADO

D1.5/6.ADO.NF

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

Weight(1 pce) g

50

6.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA399730R1700

Pkg
qty

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²IEC17.5 A
180 A
1000 V
8000 V
IP20

RoHS

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

EAC

4

6 mm 0.236 in spacing

Accessories
Description

2
1
2
3

3

4

5

6

7

9

8

10

Color

7
8

10 mm
0.394 in
3 mm
0.118 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)20 poles
32 A (IEC)
Cross spacing jumpers 2 poles
35 A (IEC)
Circuit separators 0 mm
0 in
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
Test plugs
DIA 2 mm 0.079 in
Shield connectors

9

Tools

4
5
6

End stops
End sections
Jumper bars

10 Terminal block
markers

Semi automatic tool
Hand tool
Blank card

Beige
Beige

Grey

Black

White

Type
BAM2
FEMAD3
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
BJS6-20
EL6
SCAD
AL2
AL3
FC2
CBM5
CBM8
OUPAD
OUMAD
RC610
RC65

Part Numbers
1SNA296351R0000
1SNA399802R0500
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA174784R2000
1SNA173627R2100
1SNA196896R0000
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA178745R1400
1SNA178746R1500
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100
1SNA232000R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
50
50
100
50
50
1
1
10
10

12.00
2.50
4.40
6.70
8.90
11.20
22.40
26.70
0.10
0.7
0.90
1.20
2.00
1
1
205.00
29.00
7.50
3.60
1SNC167032S0201

1

PAGE 111

D2.5/8.ADO.NF IDC terminal blocks
Feed-through - ADO System® - 8 mm 0.315 in spacing
2.61 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

1SNC163112F0014

Ordering details
Description

Color

Feed-through

TypePart Numbers

D2.5/8.ADO.NF

Beige

Main technical data
Connecting capacity
ADO

Flexible without ferrule

D2.5/8.ADO.NF

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

RoHS

1SNA399736R0100

Pkg

Weightqty(1 pce) g

50

9.00

Mounting instructions
NF F 63-808

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
24 A
300 A
1000 V
8000 V
IP20

EN 50306

Rail

1 … 2.5 mm²

Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
50
50
100
10
1
1
10

12.00
2.50
4.50
6.00
10.00
12.20
20.00
0.10
0.7
0.90
1.20
2.00
10.00
205.00
29.00
8.20

NF F 61-017
16 A
500 V

EAC

4

8 mm 0.315 in spacing

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

10 mm
0.394 in
3 mm
0.118 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Cross spacing jumpers 2 poles
35 A (IEC)
Circuit separators 0 mm
0 in
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
Test plugs
DIA 2 mm 0.079 in
DIA 4 mm 0.157 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Beige
Beige

Grey

Black
White

White

Type
BAM2
FEMAD3
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
EL6
SCAD
AL2
AL3
FC2
FC4
OUPAD
OUMAD
RC810

1SNA296351R0000
1SNA399802R0500
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA173627R2100
1SNA196896R0000
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA167860R0100
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

1SNC167058S0201

9

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

D2.5/8.ADO.NF1 IDC terminal blocks
Feed-through - ADO System® - 8 mm 0.315 in spacing
1.5 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Black marking to identify wire size.

1SNC163118F0014

Ordering details
Description

Color

Feed-throughMain technical data
ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
48,5 1.91"

CE

RoHS

1SNA399749R2600

Pkg

Weightqty(1 pce) g

50

9.00

Mounting instructions
NF F 63-808

Flexible without ferrule

D2.5/8.ADO.NF1

56 2.20"

Part Numbers

D2.5/8.ADO.NF1

Beige

Connecting capacity

45,5 1.79"

Type

IEC
24 A
180 A
1000 V
8000 VIP20

NF F 63-296
NF F 63-826
1.5 mm²

EN 50306

Rail
Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

EAC

4

8
.315"

24 .95"8 mm 0.315 in spacing

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

10 mm
0.394 in
3 mm
0.118 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Cross spacing jumpers 2 poles
35 A (IEC)
Circuit separators 0 mm
0 in
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
Test plugs
DIA 2 mm 0.079 in
DIA 4 mm 0.157 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Beige
Beige

Grey

Black
White

White

Type
BAM2
FEMAD3
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
EL6
SCAD
AL2
AL3
FC2
FC4
OUPAD
OUMAD
RC810

Part Numbers
1SNA296351R0000
1SNA399802R0500
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA173627R2100
1SNA196896R0000
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA167860R0100
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
50
50
100
10
1
1
10

12.00
2.50
4.50
6.00
10.00
12.20
20.00
0.10
0.7
0.90
1.20
2.00
10.00
205.0029.00
8.20

1SNC167013S0201

9

PAGE 113

D4/8.ADO.NF IDC terminal blocks
Feed-through - ADO System® - 8 mm 0.315 in spacing
4.32 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Yellow marking to identify wire size.

Ordering details
1SNC167096V0014

Description

Color

Feed-throughMain technical data
ADO

Flexible without ferrule

D4/8.ADO.NF

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
48,5 1.91"

45,5 1.79"

56 2.20"

Part Numbers

D4/8.ADO.NF

Beige

Connecting capacity

4

Type

CE

RoHS

1SNA399748R2500

Pkg

Weightqty(1 pce) g

50

9.00

Mounting instructions
NF F 63-808

NF F 63-296
NF F 63-826

EN 50306

4.32 mm²
IEC
32 A
480 A
1000 V
8000 V
IP20

Rail
Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
50
50
100
10
1
1
10

12.00
2.50
4.50
6.00
10.00
12.20
20.00
0.10
0.7
0.90
1.20
2.00
10.00
205.00
29.00
8.20

NF F 61-017
16 A
500 V

EAC

8
.315"

24 .95"8 mm 0.315 in spacing

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

10 mm
0.394 in
3 mm
0.118 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Cross spacing jumpers 2 poles
35 A (IEC)
Circuit separators 0 mm
0 in
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
Test plugs
DIA 2 mm 0.079 in
DIA 4 mm 0.157 in
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card
End stops
End sections
Jumper bars

Color
Beige
Beige

Grey

Black
White

White

Type
BAM2
FEMAD3
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
EL6
SCAD
AL2
AL3
FC2
FC4
OUPAD
OUMAD
RC810

1SNA296351R0000
1SNA399802R0500
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA173627R2100
1SNA196896R0000
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA167860R0100
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

1SNC167062S0201

9

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD1.5/6.S.ADO.NF IDC terminal blocks
Disconnect with plug - ADO System® - 6 mm 0.236 in spacing

1SNC163084F0014

1.82 mm²

Description–– Ease your disconnect operations with the disconnect component holder plug,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
Description

Color
With 2 test sockets
DIA 2 mm 0.079 in

Disconnect

Type

Beige

Part Numbers

D1.5/6.S.ADO.NF

Main technical data

D1.5/6.S.ADO.NF

Connecting capacity
ADO

Flexible without ferrule

48 1.89"

55,5 2.18"

68,5 2.70"

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

RoHS

1SNA400083R2500

Pkg

Weightqty(1 pce) g

50

8.00

Mounting instructions
NF F 63-808

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²
IEC
10 A
180 A
500 V
6000 V
IP20

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017

4

EAC

6
.236"

37 1.46"

6 mm 0.236 in spacing

Accessories
1

Description

2
1
2
3

3

5

4

6

4
5
6
7

End stops
10 mm
0.394 inEnd sections
2 mm
0.079 inComponent plugs With solder leads andscrewsFor 5x20 and 5x25 fuses
Short circuit plugs Equipped with linking bar
Extraction tools
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Beige
Beige
Beige

Beige

White

Type
BAM2
FEDAD5BNSV62BNSV62-1
BNF652
BNC62
EXBN2
OUPAD
OUMAD
RC610

Part Numbers
1SNA296351R0000
1SNA399804R0700
1SNA196854R1500
1SNA400142R0400
1SNA196998R1600
1SNA196853R1400
1SNA171018R2000
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
1
1
1
10

12.00
2.70
6.00
6.00
6.00
7.00
205.0029.00
7.50

1SNC167080S0201

7

PAGE 115

D2.5/8.S.ADO.NF IDC terminal blocks
Disconnect with plug - ADO System® - 8 mm 0.315 in spacing

1SNC163076F0014

2.61 mm²

Description–– Ease your disconnect operations with the disconnect component holder plug,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

Ordering details
Description

Color
With 2 test sockets
DIA 2 mm 0.079 in

Disconnect

Type

Beige

Part Numbers

D2.5/8.S.ADO.NF

Main technical data

D2.5/8.S.ADO.NF

Connecting capacity
ADO

Flexible without ferrule

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

4

CE

RoHS

1SNA399752R1100

Pkg

Weightqty(1 pce) g

50

11.00

Mounting instructions
NF F 63-808

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
15 A
300 A
500 V
6000 V
IP20

EN 50306

Rail

1 … 2.5 mm²

Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
50
50
50
1
1
1
10

12.00
2.70
8.00
8.00
9.00

NF F 61-017

EAC

8 mm 0.315 in spacing

Accessories
1

Description

2
1
2
3

3

4
4
5
6

5

6

7

End stops
10 mm
0.394 inEnd sections
2 mm
0.079 inComponent plugs For 5x20 and 5x25 fuses
With solder leads and screws
Short circuit plugs Equipped with linking bar
Extraction tools
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank card

Color
Beige
Beige
Beige
Beige

White

Type
BAM2
FEDAD5
BNF52
BNSV82
BNCT82
EXBN2
OUPAD
OUMAD
RC810

1SNA296351R0000
1SNA399804R0700
1SNA196924R0300
1SNA196927R0600
1SNA196926R0500
1SNA171018R2000
1SNA178944R0400
1SNA179466R0600
1SNA234000R0200

205.0029.00
8.20

1SNC167078S0201

7

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD1.5/6.D2.ADO.NF IDC terminal blocks
Feed-through - ADO System® - 6 mm 0.236 in spacing

1SNC167149F0014

1.82 mm²

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 6 mm 0.236 in
spacing,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
Description

Color

Feed-through

TypePart Numbers

D1.5/6.D2.ADO.NF

Beige

Main technical data
Connecting capacity
D1.5/6.D2.ADO.NF

ADO

83 3.27"
75,5 2.97"

93 3.66"

Flexible without ferrule

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

RoHS

1SNA399742R1700

Pkg

Weightqty(1 pce) g

50

18.00

Mounting instructions
NF F 63-808

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²IEC17.5 A
180 A
800 V
6000 V
IP20

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

4

EAC

6
.236"

52,6 2.07"

6 mm 0.236 in spacing

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8

12 mm
0.472 in
5 mm
0.197 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)20 poles
32 A (IEC)
Circuit separators 0 mm
0 in
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
Test plugs
DIA 2 mm 0.079 in
Tools
Semi automatic tool
Hand tool
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

Color
Grey
Beige

Grey

Black

White

Type
BADH
FED2AD2
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
BJS6-20
SCAD
AL2
AL3
FC2
OUPAD
OUMAD
RC610
RC65

Part Numbers
1SNA116900R2700
1SNA399803R0600
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA174784R2000
1SNA196896R0000
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100
1SNA232000R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
50
50
100
1
1
10
10

20.00
7.00
4.40
6.70
8.90
11.20
22.40
26.70
0.7
0.90
1.20
2.00
205.00
29.00
7.50
3.60

1SNC167037S0201

1

PAGE 117

D1.5/6.ADO.D2.NF IDC terminal blocks
Component holder - ADO System® - 6 mm 0.236 in spacing

1SNC167062F0014

1.82 mm²

Description–– Terminal block equipped with a 1N5408 diode in series,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
Description

Color
Equipped with
1N5408 diode

Component holder

Type

Beige

Part Numbers

D1.5/6.ADO.D2.NF

Main technical data
ADO

NF F 63-808

Flexible without ferruleCE

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²IEC
Rated current
1A
Rated short-time withstand current (1s)
Rated voltage
80 V
Impulse withstand voltage
Protection
IP20

4

Weight(1 pce) g

50

7.00

Mounting instructions

Connecting capacity
D1.5/6.ADO.D2.NF

1SNA399916R2600

Pkg
qty

RoHS

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017

EAC

6 mm 0.236 in spacing

Accessories
1

3

Color

1
2
3

End stops
10 mm
End sections
3 mm
Shield connectors

4

Tools

5

Terminal block
markers

4

0.394 in
0.118 inSemi automatic tool
Hand tool
Blank card

Beige
Beige

White

Type
BAM2
FEMAD3
CBM5
CBM8
OUPAD
OUMAD
RC610
RC65

Part Numbers
1SNA296351R0000
1SNA399802R0500
1SNA178745R1400
1SNA178746R1500
1SNA178944R0400
1SNA179466R0600
1SNA233000R0100
1SNA232000R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
1
1
10
10

12.00
2.50
1
1
205.00
29.00
7.50
3.60

1SNC167005S0201

5

Description

2

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD1.5/7.ADO-CPE.NF pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167113V0014

1.82 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
Description

Color

1 ADO - 1 pluggable

1 circuit

TypePart Numbers

D1.5/7.ADO-CPE.NF

Beige

Main technical data
Connecting capacity
D1.5/7.ADO-CPE.NF

ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

Weight(1 pce) g

50

8.40

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400153R0700

Pkg
qty

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²
IEC
16 A
180 A
500 V

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

IP20

RoHS

4

EAC

Compatible products

7.62 mm 0.3 in spacing

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8
7

Color
10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Numbers
1SNA296351R0000
1SNA400019R0400
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

8

1SNC167009S0201

1

PAGE 119

D2.5/7.ADO-CPE.NF1 pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167115V0014

1.5 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Black marking to identify wire size.

Ordering details
Description

Color

1 ADO - 1 pluggable

1 circuit

TypePart Numbers

D2.5/7.ADO-CPE.NF1

Beige

Main technical data
Connecting capacity
D2.5/7.ADO-CPE.NF1

ADO

4

Flexible without ferrule

CE

Weight(1 pce) g

50

8.40

Mounting instructions
NF F 63-808

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

1SNA400156R0200

Pkg
qty

IEC
24 A
180 A
500 V

NF F 63-296
NF F 63-826
1.5 mm²

EN 50306

Rail
Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

NF F 61-017
16 A
500 V

IP20

RoHS

EAC

Compatible products

7.62 mm 0.3 in spacing

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8

10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

1SNA296351R0000
1SNA400019R0400
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

8

1SNC167010S0201

7

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD1.5/7.2ADO-CPE.NF pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167117V0014

1.82 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
Description

Color

2 ADO - 1 pluggable
D1.5/7.2ADO-CPE.NF

1 circuit

TypePart Numbers

D1.5/7.2ADO-CPE.NF

Beige

Main technical data
Connecting capacity
ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

Weight(1 pce) g

50

11.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400154R0000

Pkg
qty

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²
IEC
16 A
180 A
500 V

EN 50306Rail

0.5 … 1.5 mm² Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

IP20

RoHS

4

EAC

Compatible products
7.62 mm 0.3 in spacing

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8
7

Color
10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.2ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Numbers
1SNA296351R0000
1SNA400018R0300
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

8

1SNC167071S0201

1

PAGE 121

D2.5/7.ADO-CPE.NF pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167114V0014

2.61 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

Ordering details
Description

Color

1 ADO - 1 pluggable

1 circuit

TypePart Numbers

D2.5/7.ADO-CPE.NF

Beige

Main technical data
Connecting capacity
D2.5/7.ADO-CPE.NF

ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

4

CE

Weight(1 pce) g

50

8.40

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400061R0600

Pkg
qty

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
24 A
300 A
500 V

EN 50306

Rail

1 … 2.5 mm²

Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

NF F 61-017
16 A
500 V

IP20

RoHS

EAC

Compatible products

7.62 mm 0.3 in spacing

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8

10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

1SNA296351R0000
1SNA400019R0400
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

8

1SNC167076S0201

7

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

D2.5/7.2ADO-CPE.NF pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167118V0014

2.61 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

Ordering details
Description

Color

2 ADO - 1 pluggable
D2.5/7.2ADO-CPE.NF

1 circuit

TypePart Numbers

D2.5/7.2ADO-CPE.NF

Beige

Main technical data
Connecting capacity
ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

Weight(1 pce) g

50

11.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400062R0700

Pkg
qty

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
24 A
300 A
500 V

EN 50306

Rail

1 … 2.5 mm²

Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

IP20

RoHS

4

EAC

Compatible products
7.62 mm 0.3 in spacing

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8
7

Color
10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.2ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Numbers
1SNA296351R0000
1SNA400018R0300
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

8

1SNC167006S0201

1

PAGE 123

D4/7.ADO-CPE.NF pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167116V0014

4.32 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Yellow marking to identify wire size.

Ordering details
Description

Color

1 ADO - 1 pluggable

1 circuit

TypePart Numbers

D4/7.ADO-CPE.NF

Beige

Main technical data
Connecting capacity
D4/7.ADO-CPE.NF

ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

4

CE

Weight(1 pce) g

50

8.40

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400240R2200

Pkg
qty

NF F 63-296
NF F 63-826

EN 50306

4.32 mm²
IEC
24 A
480 A
500 V

Rail
Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

NF F 61-017
16 A
500 V

IP20

RoHS

EAC

Compatible products

7.62 mm 0.3 in spacing

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8

10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

1SNA296351R0000
1SNA400019R0400
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

8

1SNC167070S0201

7

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD4/7.2ADO-CPE.NF pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing

1SNC167120V0014

4.32 mm²

Description–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Yellow marking to identify wire size.

Ordering details
Description

Color

2 ADO - 1 pluggable
D4/7.2ADO-CPE.NF

1 circuit

TypePart Numbers

D4/7.2ADO-CPE.NF

Beige

Main technical data
Connecting capacity
ADO

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

Weight(1 pce) g

50

11.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SNA400241R1700

Pkg
qty

NF F 63-296
NF F 63-826

EN 50306

4.32 mm²
IEC
24 A
480 A
500 V

Rail
Tool

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

IP20

RoHS

4

EAC

Compatible products
7.62 mm 0.3 in spacing

Accessories

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Tools

4

6

8
7

Color
10 mm
0.394 in
2.9 mm
0.114 in10 poles2 poles
5 poles
For jumper bars type BJE762

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Beige
OrangeOrangeBlack
Yellow

White

Type
BAM2
FECPE.2ADO
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCE
OUPAD
OUMAD
RB-12W7

Part Numbers
1SNA296351R0000
1SNA400018R0300
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
1
1
50

12.00
2.20
24.00
5.30
15.40
100.000.40
1.00
205.00
29.00
6.00

8

1SNC167008S0201

1

PAGE 125

D2.5/7.2CPE pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing
Description

1SNC167095V0014–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– 1 plug on each side: 1 circuit.

Ordering details
DescriptionColor
1 circuit

2 pluggables

Type

Part Numbers

D2.5/7.2CPE

Beige

Main technical data
Connecting capacity
D2.5/7.2CPE

ADO

37 1.46"44.5 1.75"

54.7 2.15"

NF F 63-296
NF F 63-826

EN 50306

Flexible without ferrule

CE

Weight(1 pce) g

50

7.00

Mounting instructions
NF F 63-808

IEC
Rated current
16 A
Rated short-time withstand current (1s)
Rated voltage
500 V
Impulse withstand voltage
Protection
IP20

27.4 1.08"

1SNA400703R1700

Pkg
qty

RoHS

Rail
Tool

TH 35-7.5,
TH 35-15
ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
50

12.00
1.90
24.00
5.30
15.40
100.00
0.40
1.00
6.00

NF F 61-017
16 A
500 V

EAC

7.6
0.3"

4

Compatible products

7.62 mm 0.3 in spacing

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Terminal block markers Blank strip marker

4

6

Color
10 mm
0.394 in
2.8 mm0.11 in10 poles2 poles
5 poles
For jumper bars type BJE762

Beige
Beige
OrangeOrangeBlack
Yellow
White

Type
BAM2
FECPE
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCERB-12W7

1SNA296351R0000
1SNA400708R2400
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA290455R0700

1SNC167050S0201

7

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

D2.5/7.CPE.CPE pluggable terminal blocks
Feed-through - ADO System® - 7.62 mm 0.3 in spacing
Description

1SNC167121V0014–– Increase your productivity with pluggable terminal blocks: possibility of pre-produced plugs harnesses, timesaving plug & play assembly,–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– 1 plug on each side: 2 circuits.

Ordering details
DescriptionColor
2 circuits

2 pluggables

Type

Part Numbers

D2.5/7.CPE.CPE

Beige

Main technical data
Connecting capacity
D2.5/7.CPE.CPE

ADO

37 1.46"44.5 1.75"

54.7 2.15"

NF F 63-296
NF F 63-826

EN 50306

Flexible without ferrule

CE

Weight(1 pce) g

50

7.00

Mounting instructions
NF F 63-808

RoHS

Rail
Tool

IEC
Rated current
16 A
Rated short-time withstand current (1s)
Rated voltage
500 V
Impulse withstand voltage
Protection
IP20

27.4 1.08"

1SNA400704R1000

Pkg
qty

TH 35-7.5,
TH 35-15
ADO system tool

NF F 61-017
16 A
500 V

EAC

7.6
0.3"

4

Compatible products

7.62 mm 0.3 in spacing

Accessories
1

3

5

Description

2
1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Insulating tips
Locking devices
Coding pegs
Terminal block markers Blank strip marker

4

6

Color
10 mm
0.394 in
2.8 mm0.11 in10 poles2 poles
5 poles
For jumper bars type BJE762

Beige
Beige
OrangeOrangeBlack
Yellow
White

Type
BAM2
FECPE
BJE762.10
BJE762.2
BJE762.5
EIP
VRADO.CPE7
COCERB-12W7

Part Numbers
1SNA296351R0000
1SNA400708R2400
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA290454R0600
1SNA400063R0000
1SNA199321R2100
1SNA290455R0700

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
20
10
50

12.00
1.90
24.00
5.30
15.40
100.00
0.40
1.00
6.00

1SNC167031S0201

7

PAGE 127

L 266 200 15 female plugs
ADO System® - 7.62 mm 0.3 in spacing

1SNC167127V0014

1.82 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
DescriptionColor
2 poles
3 poles
4 poles
5 poles
6 poles
7 poles
8 poles
9 poles
10 polesFemale plugs

7.62 0.30"

L 266 200 15

Part Numbers

FIC F.ADO.T1.2P.NF
FIC F.ADO.T1.3P.NF
FIC F.ADO.T1.4P.NF
FIC F.ADO.T1.5P.NF
FIC F.ADO.T1.6P.NF
FIC F.ADO.T1.7P.NF
FIC F.ADO.T1.8P.NF
FIC F.ADO.T1.9P.NF
FIC F.ADO.T1.10P.NF

Beige
Beige
Beige
Beige
Beige
Beige
Beige
Beige
Beige

Main technical data
L

Connecting capacity

7.62 0.30"

ADO

Flexible without ferrule28.5 1.12"

22.4 0.88"

CE

RoHS

1SSS266202R8800
1SSS266203R8800
1SSS266204R8800
1SSS266205R8800
1SSS266206R8800
1SSS266207R8800
1SSS266208R8800
1SSS266209R8800
1SSS266210R8800

Pkg

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50

6.00
10.00
13.00
16.00
19.00
22.00
26.00
29.00
32.00

Mounting instructions
NF F 63-808

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

4

20.3 0.80"

Type

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²IEC
16 A
218.4 A
500 V

EN 50306Rail

0.5 … 1.5 mm² Tool

ADO system tool

NF F 61-017
16 A
500 V

IP20

USR CNR

EAC

Compatible products

L = nb poles x 7.62
7.62 mm 0.3 in spacing

1

3

Description

2

4

1

Cable clamps

2
3

Coding pegs
Tools

4

Color
Used on products from 3 to 7 poles
Used on products from 8 to 16 poles

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Beige
Yellow

White

Type
PT1
PT2
COCF
OUPAD
OUMAD
RB-12W7

Part Numbers
1SSS299253R2800
1SSS299254R2800
1SNA199320R0400
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

20
20
10
1
1
50

1.60
4.80
1.00
205.0029.00
6.00

1SNC167011S0201

Accessories

L 266 200 25 female plugs with brackets
ADO System® - 7.62 mm 0.3 in spacing

1SNC167124V0014

1.82 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
DescriptionColor
2 poles
3 poles
4 poles
5 poles
6 poles
8 poles
10 polesFemale plugs

L 266 200 25

TypePart Numbers

FIC F.ADO.T1.B.2P.NF
FIC F.ADO.T1.B.3P.NF
FIC F.ADO.T1.B.4P.NF
FIC F.ADO.T1.B.5P.NF
FIC F.ADO.T1.B.6P.NF
FIC F.ADO.T1.B.8P.NF
FIC F.ADO.T1.B.10P.NF

Beige
Beige
Beige
Beige
Beige
Beige
Beige

Main technical data
7.62 0.30"

Connecting capacity

50
50
50
50
50
50
50

7.40
10.00
14.00
18.00
21.00
28.00
35.00

Mounting instructions
NF F 63-808

Flexible without ferrule

Weight(1 pce) g

NF F 63-296
NF F 63-826

0.6 … 1.82 mm²EN 50306Rail

0.5 … 1.5 mm² Tool

ADO system toolL

ADO

1SSS266202R9800
1SSS266203R9800
1SSS266204R9800
1SSS266205R9800
1SSS266206R9800
1SSS266208R9800
1SSS266210R9800

Pkg
qty

7.62 0.30"

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22.4 0.88"

CE

RoHS

NF F 61-017
16 A
500 V
4

IP20

USR CNR

EAC

Compatible products
28.5 1.12"

20.3 0.80"

10.3
0.41"

IEC
16 A
218.4 A
500 V

L = (nb poles x 7.62) + 13.7
7.62 mm 0.3 in spacing

Accessories

3

Description

2

4

1

Cable clamps

2
3

Coding pegs
Tools

4

Color
Used on products from 3 to 7 poles
Used on products from 8 to 16 poles

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Yellow

White

Type
PT1
PT2
COCF
OUPAD
OUMAD
RB-12W7

Part Numbers
1SSS299253R2800
1SSS299254R2800
1SNA199320R0400
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

20
20
10
1
1
50

1.60
4.80
1.00
205.0029.00
6.00

1SNC167038S0201

1

PAGE 129

L 277 200 15 female plugs
ADO System® - 7.62 mm 0.3 in spacing

1SNC167129V0014

1.5 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Black marking to identify wire size.

Ordering details
DescriptionColor
2 poles
3 poles
4 poles
5 poles
6 poles

Female plugs

L 277 200 15

TypePart Numbers

FIC F.ADO.T3-.2P.NF
FIC F.ADO.T3-.3P.NF
FIC F.ADO.T3-.4P.NF
FIC F.ADO.T3-.5P.NF
FIC F.ADO.T3-.6P.NF

Beige
Beige
Beige
Beige
Beige

Main technical data
7.62 0.30"

Connecting capacity
Flexible without ferrule7.62 0.30"

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Weight(1 pce) g

50
50
50
50
50

6.00
10.00
13.00
16.00
19.00

Mounting instructions
NF F 63-808

L

ADO

1SSS277202R8800
1SSS277203R8800
1SSS277204R8800
1SSS277205R8800
1SSS277206R8800

Pkg
qty

IEC
24 A
180 A
500 V

NF F 63-296
NF F 63-826
1.5 mm²

EN 50306

Rail
Tool

ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

20
20
10
1
1
50

1.60
4.80
1.00
205.00
29.00
6.00

NF F 61-017
16 A
500 V

IP20

4
22.4 0.88"

20.3 0.80"

28.5 1.12"

CE

RoHS

EAC

Compatible products

L = nb poles x 7.62
7.62 mm 0.3 in spacing

Accessories
1

3

Description

2

4

1

Cable clamps

2
3

Coding pegs
Tools

Used on products from 3 to 7 poles
Used on products from 8 to 16 poles

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Yellow

White

Type
PT1
PT2
COCF
OUPAD
OUMAD
RB-12W7

1SSS299253R2800
1SSS299254R2800
1SNA199320R0400
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

1SNC167015S0201

4

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSL 267 200 15 female plugs
ADO System® - 7.62 mm 0.3 in spacing
Description

2.61 mm²

1SNC167128V0014–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

Ordering details
DescriptionColor
2 poles
3 poles
4 poles
5 poles
6 poles
7 poles
8 poles
10 polesFemale plugs

7.62 0.30"

L 267 200 15

FIC F.ADO.T2.2P.NF
FIC F.ADO.T2.3P.NF
FIC F.ADO.T2.4P.NF
FIC F.ADO.T2.5P.NF
FIC F.ADO.T2.6P.NF
FIC F.ADO.T2.7P.NF
FIC F.ADO.T2.8P.NF
FIC F.ADO.T2.10P.NF

Beige
Beige
Beige
Beige
Beige
Beige
Beige
Beige

7.62 0.30"

Flexible without ferrule

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
28.5 1.12"

22.4 0.88"

CE

RoHS

1SSS267202R8800
1SSS267203R8800
1SSS267204R8800
1SSS267205R8800
1SSS267206R8800
1SSS267207R8800
1SSS267208R8800
1SSS267210R8800

Weightqty(1 pce) g

50
50
50
50
50
50
50
50

6.00
10.00
13.00
16.00
19.00
22.00
26.00
32.00

Mounting instructions
NF F 63-808

L

Connecting capacity

Pkg

Part Numbers

Main technical data
ADO

20.3 0.80"

Type

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
24 A
313.2 A
500 V

EN 50306

Rail

1 … 2.5 mm²Tool

ADO system tool

NF F 61-017
16 A
500 V

4

IP20

USR CNR

EAC

Compatible products
L = nb poles x 7.62
7.62 mm 0.3 in spacing

Accessories

3

Description

2

4

1

Cable clamps

2
3

Coding pegs
Tools

4

Color
Used on products from 3 to 7 poles
Used on products from 8 to 16 poles

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Yellow

White

Type
PT1
PT2
COCF
OUPAD
OUMAD
RB-12W7

Part Numbers
1SSS299253R2800
1SSS299254R2800
1SNA199320R0400
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

20
20
10
1
1
50

1.60
4.80
1.00
205.0029.00
6.00
1SNC167012S0201

1

PAGE 131

L 267 200 25 female plugs with brackets
ADO System® - 7.62 mm 0.3 in spacing

1SNC167125V0014

2.61 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

Ordering details
DescriptionColor
2 poles
3 poles
4 poles
5 poles
6 poles
8 poles
10 poles
16 polesFemale plugs

L 267 200 25

Part Numbers

FIC F.ADO.T2.B.2P.NF
FIC F.ADO.T2.B.3P.NF
FIC F.ADO.T2.B.4P.NF
FIC F.ADO.T2.B.5P.NF
FIC F.ADO.T2.B.6P.NF
FIC F.ADO.T2.B.8P.NF
FIC F.ADO.T2.B.10P.NF
FIC F.ADO.T2.B.16P.NF

Beige
Beige
Beige
Beige
Beige
Beige
Beige
Beige

7.62 0.30"

Main technical data
Connecting capacity
L

ADO

7.62 0.30"

4

Type

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

Weight(1 pce) g

50
50
50
50
50
50
50
20

7.40
11.00
14.00
18.00
21.00
28.00
35.00
57.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SSS267202R9800
1SSS267203R9800
1SSS267204R9800
1SSS267205R9800
1SSS267206R9800
1SSS267208R9800
1SSS267210R9800
1SSS267216R9800

Pkg
qty

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
24 A
313.2 A
500 V

EN 50306

Rail

1 … 2.5 mm²Tool

ADO system toolPart Numbers

Pkg

Weightqty(1 pce) g

20
20
10
1
1
50

1.60
4.80
1.00
205.00
29.00
6.00

NF F 61-017
16 A
500 V

IP20

22.4 0.88"
10.3
0.41"

RoHS

USR CNR

EAC

Compatible products

28.5 1.12"

20.3 0.80"

CE

L = (nb poles x 7.62) + 13.7
7.62 mm 0.3 in spacing

Accessories
1

3

Description

2

4

1

Cable clamps

2
3

Coding pegs
Tools

Used on products from 3 to 7 poles
Used on products from 8 to 16 poles

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Yellow

White

Type
PT1
PT2
COCF
OUPAD
OUMAD
RB-12W7

1SSS299253R2800
1SSS299254R2800
1SNA199320R0400
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

1SNC167041S0201

4

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSL 276 200 15 female plugs
ADO System® - 7.62 mm 0.3 in spacing

1SNC167130V0014

4.32 mm²

L 276 200 15

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Yellow marking to identify wire size.

Ordering details
Description

Color
4 poles
5 poles

Female plugs

TypePart Numbers

FIC F.ADO.T3.4P.NF
FIC F.ADO.T3.5P.NF

Beige
Beige

Main technical data
Connecting capacity

7.62 0.30"

ADO

7.62 0.30"

L

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

RoHS

Weight(1 pce) g

50
50

13.00
16.00

Mounting instructions
NF F 63-808

Flexible without ferrule

1SSS276204R8800
1SSS276205R8800

Pkg
qty

NF F 63-296
NF F 63-826

EN 50306

4.32 mm²
IEC
24 A
518.4 A
500 V

Rail
Tool

ADO system tool

NF F 61-017
16 A
500 V

IP20

USR CNREAC

4
22.4 0.88"

20.3 0.80"

28.5 1.12"

Compatible products

L = nb poles x 7.62
7.62 mm 0.3 in spacing

Accessories

3

Description

2

4

1

Cable clamps

2
3

Coding pegs
Tools

4

Color
Used on products from 3 to 7 poles
Used on products from 8 to 16 poles

Semi automatic tool
Hand tool
Terminal block markers Blank strip marker

Beige
Yellow

White

Type
PT1
PT2
COCF
OUPAD
OUMAD
RB-12W7

Part Numbers
1SSS299253R2800
1SSS299254R2800
1SNA199320R0400
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

20
20
10
1
1
50

1.60
4.80
1.00
205.0029.00
6.00

1SNC167014S0201

1

PAGE 133

L 366 200 45 male plugs with flanges and inserts
ADO System® - 7.62 mm 0.3 in spacing

1SNC167131V0014

1.82 mm²

Description–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Red marking to identify wire size.

Ordering details
Description

Color

Type

Part Numbers

2 poles
3 poles
4 poles
5 poles
6 poles
8 poles
10 polesMale plugs

L 366 200 45

FIC M.ADO.T1.FI.2P.NF
FIC M.ADO.T1.FI.3P.NF
FIC M.ADO.T1.FI.4P.NF
FIC M.ADO.T1.FI.5P.NF
FIC M.ADO.T1.FI.6P.NF
FIC M.ADO.T1.FI.8P.NF
FIC M.ADO.T1.FI.10P.NF

Beige
Beige
Beige
Beige
Beige
Beige
Beige

Main technical data
7.62 0.30"

Connecting capacity
ADO

Flexible without ferrule

L

CE

RoHS

USR CNR

1SSS366202R4100
1SSS366203R4100
1SSS366204R4100
1SSS366205R4100
1SSS366206R4100
1SSS366208R4100
1SSS366210R4100

Weight(1 pce) g

50
50
50
50
50
50
50

Mounting instructions
NF F 63-808

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

7.62 0.30"

4

Pkg
qty

NF F 63-296
NF F 63-826

EN 50306

0.6 … 1.82 mm²IEC
16 A
218.4 A
500 V

Rail

0.5 … 1.5 mm² Tool

ADO system tool

NF F 61-017
16 A
500 V

IP20

EAC

Compatible products

24.4 0.96"

27.1 1.07"

A

A: Panel feed-through or base mounting
B: Panel feed-through drilling
L1 = (nb poles x 7.62) + 15.24
L2 = (nb poles x 7.62) + 22.86

L 266 200 25

L = (nb poles x 7.62) + 31.5

B

7.62 mm 0.3 in spacing

C: Base drilling
L3 = (nb poles x 7.62) + 22.86
a: M2.5 or M3 insert on panel

L 267 200 25

L1
L2

L 276 200 25

C

L3

a

1

Description

2
1
2

3
3

Used on products from 3 to 7 poles
Used on products from 8 to 16 poles
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank strip marker
Cable clamps

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color
Beige

White

Type
PT1
PT2
OUPAD
OUMAD
RB-12W7

Part Numbers
1SSS299253R2800
1SSS299254R2800
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

20
20
1
1
50

1.60
4.80
205.0029.00
6.00

1SNC167019S0201

Accessories

L 367 200 45 male plugs with flanges and inserts
ADO System® - 7.62 mm 0.3 in spacing
Description

2.61 mm²

1SNC167132V0014–– With the TE Connectivity ADO System®, experience the fastest and most reliable connection on the market,–– Designed for rolling stock applications exposed to severe constrains (vibrations, shocks etc.),–– Up to 2 wires per connection,–– Blue marking to identify wire size.

Ordering details
Description

Color

Type

Pkg

Part Numbers

qty

2 poles
3 poles
4 poles
5 poles
6 poles
8 poles
10 polesMale plugs

L 367 200 45

FIC M.ADO.T2.FI.2P.NF
FIC M.ADO.T2.FI.3P.NF
FIC M.ADO.T2.FI.4P.NF
FIC M.ADO.T2.FI.5P.NF
FIC M.ADO.T2.FI.6P.NF
FIC M.ADO.T2.FI.8P.NF
FIC M.ADO.T2.FI.10P.NF

Beige
Beige
Beige
Beige
Beige
Beige
Beige

Main technical data
7.62 0.30"

Connecting capacity
ADO

7.62 0.30"

L

Rated current
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

CE

RoHS

50
50
50
50
50
50
50

Mounting instructions
NF F 63-808

Flexible without ferrule

1SSS367202R4100
1SSS367203R4100
1SSS367204R4100
1SSS367205R4100
1SSS367206R4100
1SSS367208R4100
1SSS367210R4100

Weight(1 pce) g

NF F 63-296
NF F 63-826

0.93 … 2.61 mm²
IEC
22 A
313.2 A
500 V

EN 50306

Rail

1 … 2.5 mm²Tool

ADO system tool

NF F 61-017
16 A
500 V
4

IP20

USR CNR

EAC

Compatible products

24.4 0.96"

27.1 1.07"

A

A: Panel feed-through or base mounting
B: Panel feed-through drilling
L1 = (nb poles x 7.62) + 15.24
L2 = (nb poles x 7.62) + 22.86

L 266 200 25

L = (nb poles x 7.62) + 31.5

B

7.62 mm 0.3 in spacing

C: Base drilling
L3 = (nb poles x 7.62) + 22.86
a: M2.5 or M3 insert on panel

L 267 200 25

L1
L2

L 276 200 25

C

L3

a

1

Description

2
1
2

3
3

Used on products from 3 to 7 poles
Used on products from 8 to 16 poles
Tools
Semi automatic tool
Hand tool
Terminal block markers Blank strip marker
Cable clamps

Color
Beige

White

Type
PT1
PT2
OUPAD
OUMAD
RB-12W7

Part Numbers
1SSS299253R2800
1SSS299254R2800
1SNA178944R0400
1SNA179466R0600
1SNA290455R0700

Pkg

Weightqty(1 pce) g

20
20
1
1
50

1.60
4.80
205.0029.00
6.00

PAGE 135

1SNC167016S0201

Accessories

5

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
Quick-connect technology

Technologies presentation				Overview								With longitudinal quick-connect tabs
2.5 mm²
HD2.5/6.2G.2G.1
6 mm²
HD6/8.2G.2G.1
HD6/8.2G.2G.2
HD6/7.5G
HD6/7.3G.2G
HD6/7.2G.3G
HD6/9.5G
HD6/9.3G.2G
HD6/9.2G.3G
Stud-quick-connect
35 mm²
HD6/22.F12G
HD6/30.F12G
Fuse holder
6 mm²

144
145
2 longitudinal tabs and 2 vertical tabs		
146
5 vertical tabs			1472 circuits-3 vertical tabs with jumper and 2 vertical tabs		
148
2 circuits-3 vertical tabs and 2 vertical tabs with jumper		149
5 vertical tabs			
150
2 circuits-3 vertical tabs with jumper and 2 vertical tabs		
151
2 circuits-3 vertical tabs and 2 vertical tabs with jumper		152
2 longitudinal tabs on each side			
2 longitudinal tabs on each side		1 M6 stud - 12 quick-connect tabs 			
1 M6 stud - 12 quick-connect tabs			

HD6/14.SF.2G.2G for 5x20mm fusesComponent holder
6 mm²
HD6/24.DHHD6/24.DHHD6/14.DHHD6/14.DG
HD6/9.SDH.1
HD6/14.SDH.1
			

HD6/14.SDH
			

138
140

153
154

		
155

For screw and solder diode-6 tabs			

156
156
For screw and solder diode-2 tabs on each side		 157For solder diode or resistor-2 tabs on each side
158
Disconnect with component holder plug
159
For screw and solder diode-8 tabs			

5

Disconnect with component holder plug for screw& solder diode 			160Disconnect with component holder plug for screw& solder diode type SKN2.5 or SKNa2		

161

Multi level longitudinal quick-connect tabs
2.5 mm²
HD2.5/6.3.3G.3G.1		
1 circuit - 6 tabs			
HD2.5/6.3.2G.2G.1.GG Top circuit with 4 tabs - Bottom circuit with 2 tabs		
HD2.5/6.3.GG1.2G.2G Top circuit with 2 tabs - Bottom circuit with 4 tabs		
HD2.5/6.3.GG.1.2GG
3 circuits - 1 tab each side 			HD2.5/6.3.2G.2G.1		
1 Top circuit with 4 tabs			
HD2.5/6.3.GH.2G.H		
1 top circuit with 1 tab & 1 solder connection -

162
163
164
165
166

				

167

Summary_5

1 bottom circuit with 2 tabs & 1 solder connection		

PAGE 137

Railway applications, terminal blocks
Quick-connect technology

The historical technology for
railway control and signal
distribution
The Quick-connect technology allows to save wiring time and isa good solution for distribution of control signal. It can be usedin case of limited space on the side (vertical version), when ahigh density connection is needed (horizontal version up to 6
connection per block) or when the power has to be distributed
from power to control circuits (1 stud input / 12 quick-connect
outputs.
CE

RoHS

EAC

Reliable in harsh conditions

Improve installation efficiency
Large and flexible offering–– Top or side connection–– Up to 6 connections in 1 block–– Easy distribution thanks to hybrid versions with both fast-on
and stud connections–– Circuit protection thanks to component holder.

1SNC167089S0201

5

Continuous operation guaranteed for rolling stock–– Environmental tests: aging, corrosion, flammability, toxicity(I2F2, V0, HL3 R22)–– Mechanical tests: vibration and shock.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSFeatures
Area dedicated to component
soldering and screwing(SKN diodes or resistors)

Compatible with both CCTU
and DIN3 rails

High density power
distribution (35 mm² / 155 A)

5

1SNC167089S0201

Control circuits (2.5 mm² / 16 A)

PAGE 139

Railway applications, terminal blocks
Quick-connect technology
Range overview from 2.5 up to 6 mm²

Feed-throughFrom 2.5 to 6 mm²

5Perforated jumpering bars
Easy to install by cutting out
the precut partitions

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHigh connection density
Top or side connection
Up to 6 connections
Flexibility of the connection angle
in 6 mm spacing

Distribution
35 mm² / 2.5 mm²

Component holder
From 2.5 to 6 mm²

5Component holders
Easy to solder diodes or resistors
for circuit protection

1SNC167093S0201

Easy distributionof up to 12 outputs
With quick-connect / studhybrid terminal blocks

PAGE 141

Railway applications, terminal blocks
Quick-connect technology

Feed-through7 mm spacing

Section
2.5 mm²
6 mm²

HD2.5/6.2G.2G.1
HD6/8.2G.2G.1

HD6/8.2G.2G.2

Stud-quick-connect

5

HD6/7.5G

HD6/7.3G.2G

Fuse holder

Section
6 mm²
35 mm² / 2.5 mm²
35 mm² / 6 mm²

HD6/14.SF.2G.2G

HD6/24.DHHD6/22.F12G
HD6/30.F12G

Multi level longitudinal quick-connect tabs-Feed-throughSection
2.5 mm²

Clamp -

HD2.5/6.3.3G.3G.1

Channels for jumpering or testing -HD2.5/6.3.2G.2G.1.GG

Test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Blown-fuse indicator

HD2.5/6.3.GG1.2G.2G

HD2.5/6.3.GG.1.2GG

9 mm spacing

HD6/7.2G.3G

HD6/9.5G

HD6/9.3G.2G

HD6/9.2G.3G

Component holder

HD6/14.DG

HD2.5/6.3.2G.2G.1

HD2.5/6.3.GH.2G.H

HD6/9.SDH.1

HD6/14.SDH.1

HD6/14.SDH

1SNC167094S0201

HD6/14.DH

5

PAGE 143

HD2.5/6.2G.2G.1 Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing

1SNC167101V0014

2.5 mm²

Description–– Connection by 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in on each side,–– Possibility of testing,–– Two jumpering options: 6 mm 0.236 in spacing with BJS61 and 7 mm 0.276 in (adding end section) with
BJH7,–– Use of jumper bars requires to cut out the precut partition,–– NF F 61-017 designation: BB0006-2G2G (1SNA160487R2500) or BB0007-2G2G (1SNA160487R2500 +FEH3).

Ordering details
DescriptionColor
1 circuit4 tabsType
HD2.5/6.2G.2G.1

Beige

Main technical data
Connecting capacity

HD2.5/6.2G.2G.1

1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers
1SNA160487R2500

Pkg

Weightqty(1 pce) g

50

7.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 125 V(Cat. C) 150 V
26 A
2.5 mm²

250 V
250 V
20 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
100
1
1000
10

12.00
12.00
1.10
1.80
1.80
1.80
1.80
2.00
0.50
0.80
3.00
4.30
2.00

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²

EAC

6 mm 0.236 in spacing

5

Accessories
1

Description

2
1

3

4

5

6

7

2
3

4
5
6

Beige
Beige

Beige
Black

White

BAM2
BAH24
FEH3
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
BJH7-2
BJH7-3
BJH7-10
SCH3
FC2
VSJ6
RDJ6
RC610

1SNA296351R0000
1SNA168355R1300
1SNA198352R0700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA168486R2000
1SNA168487R2100
1SNA168490R0000
1SNA198692R2500
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

0.10
7.50

1SNC167022S0201

7

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)2 poles
3 poles
10 polesCircuit separators 1.6 mm
0.063 in
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/8.2G.2G.1 Quick connect terminal blocks
Feed-through - 8 mm 0.315 in spacing

1SNC167025F0014

6 mm²

Description–– Connection by 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x .031 in on each side,–– Possibility of testing,–– Two jumpering options: 8 mm 0.315 in spacing with BJH8 and 9 mm 0.354 in spacing (adding end section)with BJH9,–– Use of jumper bars requires to cut out the precut partition,–– NF F 61-017 designation: BB0008-2G2G (1SNA160606R1400) or BB0009-2G2G (1SNA160606R1400 +FEH3).

Ordering details
DescriptionColor
1 circuit4 tabsType
HD6/8.2G.2G.1

Beige

Main technical data
Connecting capacity

HD6/8.2G.2G.1

1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers
1SNA160606R1400

Pkg

Weightqty(1 pce) g

50

8.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 250 V(Cat. C) 300 V
26 A
6 mm²

250 V
250 V
20 A

Rail

Type 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
6 mm²

EAC

8 mm 0.315 in spacing

5

Accessories
Description

2
1

3

4

5

6

2
3

7
4
5
6
7

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 poles2 poles
3 poles
4 poles
5 poles
10 polesCircuit separators 1.6 mm
0.063 in
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block
Blank card
markers
End stops

Color
Beige
Beige

Beige
Black

White

Type
BAM2
BAH24
FEH3
BJH8-2
BJH8-3
BJH8-4
BJH8-5
BJH8-10
BJH9-2
BJH9-3
BJH9-4BJH9-5
BJH9-10
SCH3
FC2
VSJ6
RDJ6
RC610
RC810

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA198352R0700
1SNA168456R0100
1SNA168457R0200
1SNA168458R1300
1SNA168459R1400
1SNA168356R1400
1SNA168460R1100
1SNA168461R0600
1SNA168462R0700
1SNA168463R0000
1SNA168357R1500
1SNA198692R2500
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
10
100
1
1000
10
10

12.00
12.00
1.10
0.60
0.90
1.30
1.60
3.40
1.60
1.00
1.40
1.80
3.80
4.30
2.00
0.10
7.50
8.20

1SNC167075S0201

1

PAGE 145

HD6/8.2G.2G.2 Quick connect terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

6 mm²–– Connection by 2 longitudinal tabs on one side and 2 vertical tabs on the other side for quick-connect 6.3 x
0.8 mm 0.248 x 0.031 in,–– Possibility of testing and transverse connection,–– Use of jumper bars requires to cut out the precut partition.

1SNC167087V0014

Ordering details
DescriptionColor
1 circuit4 tabsHD6/8.2G.2G.2

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

HD6/8.2G.2G.2

Type

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers
1SNA160619R1000

Pkg

Weightqty(1 pce) g

50

11.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 380 V(Cat. C) 450 V
26 A
6 mm²

380 V
380 V
20 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
100
1
1000
10
10

12.00
12.00
1.80
0.60
0.90
1.30
1.60
3.40
4.30
2.00

0.34 … 6 mm²(Cat. C) 400 V(Cat. C) 250 V
25 A
6 mm²

EAC

8 mm 0.315 in spacing

5

Accessories
1

Description

2
1

3

4

5

6

4
5
6
7

Beige
Beige

Beige
Black

White

BAM2
BAH24
FEH4
BJH8-2
BJH8-3
BJH8-4
BJH8-5
BJH8-10
SCH3
FC2
VSJ6
RDJ6
RC610
RC810

1SNA296351R0000
1SNA168355R1300
1SNA193878R2200
1SNA168456R0100
1SNA168457R0200
1SNA168458R1300
1SNA168459R1400
1SNA168356R1400
1SNA198692R2500
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100
1SNA234000R0200

0.10
7.50
8.20

1SNC167021S0201

7

2
3

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 polesCircuit separators 1.6 mm
0.063 in
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block
Blank card
markers
End stops

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD 6/7.5G Quick connect terminal blocks
Feed-through - 7 mm 0.276 in spacing
Description

6 mm²–– Connection by 5 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in,–– Possibility of transverse connection,–– Use of jumper bars requires to cut out the precut partition.

1SNC167138V0014

Ordering details
DescriptionColor
1 circuit5 tabs1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

V DC

44.5
1.75"

HD6/7.5G

Beige

Main technical data

Rated voltage V AC

Pkg

Rated current
Rated cross section

1SNA400766R1500

Weight(1 pce) g

25

Mounting instructions
NF C

DIN

NF F 61-017

320 V
320 V
25 A
6 mm²

320 V
320 V
20 A

Rail

Type 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²
320 V
320 V
25 A
6 mm²

37
1.46"

33.5 1.32"

Part Numbers

qtyConnecting capacity
HD 6/7.5G

Type

69.5 2.73"

7 mm 0.276 in spacing
CE

RoHS

EAC

5

Accessories
Description

2
1

3

4

2
3
4

5

5

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
10 polesFastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

White

Type
BAM2
BAH24
FEHD1
BJH7-2
BJH7-3
BJH7-10
VSJ6
RDJ6
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199400R0600
1SNA168486R2000
1SNA168487R2100
1SNA168490R0000
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
1
1000
10

12.00
12.00
2.00
0.50
0.80
3.00
0.10
7.50

1SNC167054S0201

1

PAGE 147

HD 6/7.3G.2G Quick connect terminal blocks
Feed-through - 7 mm 0.276 in spacing
Description

6 mm²

1SNC167140V0014–– 2 circuits: 1 circuit with 3 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of transverse connection and 1 circuit with 2 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, marked
in red,–– Use of jumper bars requires to cut out the precut partition.

Ordering details
Description

Color

Type

2 circuits

5 tabsConnecting capacity
1 conductor
per clamp

69.5 7.73"

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC

HD6/7.3G.2G

Beige

Rated current
Rated cross section

1SNA400767R1600

Weight(1 pce) g

25

Mounting instructions
NF C

DIN

NF F 61-017

320 V
320 V
25 A
6 mm²

320 V
320 V
20 A

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
1
1000
10

12.00
12.00
2.00
0.50
0.80
3.00

0.34 … 6 mm²
320 V
320 V
25 A
6 mm²

37
1.46"

44.5
1.75"

V DC
33.5 1.32"

Pkg
qty

Main technical data
HD 6/7.3G.2G

Part Numbers

7 mm 0.276 in spacing
CE

RoHS

EAC

5

Accessories
1

Description

2
1

3

4

2
3
4
5

Beige
Beige

White

Type
BAM2
BAH24
FEHD1
BJH7-2
BJH7-3
BJH7-10
VSJ6
RDJ6
RC610

1SNA296351R0000
1SNA168355R1300
1SNA199400R0600
1SNA168486R2000
1SNA168487R2100
1SNA168490R0000
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

0.10
7.50

1SNC167033S0201

5

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
10 polesFastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD 6/7.2G.3G Quick connect terminal blocks
Feed-through - 7 mm 0.276 in spacing
Description

6 mm²

1SNC167139V0014–– 2 circuits: 1 circuit with 3 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, marked in red
and 1 circuit with 2 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of transverse
connection,–– Use of jumper bars requires to cut out the precut partition.

Ordering details
Description

Color

Type

2 circuits

5 tabsConnecting capacity
1 conductor
per clamp

69.5 7.73"

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC

HD6/7.2G.3G

Beige

Rated current
Rated cross section

1SNA400768R2700

Weight(1 pce) g

25

Mounting instructions
NF C

DIN

NF F 61-017

320 V
320 V
25 A
6 mm²

320 V
320 V
20 A

Rail

Type 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²
320 V
320 V
25 A
6 mm²

37
1.46"

44.5
1.75"

V DC
33.5 1.32"

Pkg
qty

Main technical data
HD 6/7.2G.3GPart Numbers

7 mm 0.276 in spacing
CE

RoHS

EAC

5

Accessories
Description

2
1

3

4

2
3
4

5

5

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
10 polesFastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

White

Type
BAM2
BAH24
FEHD1
BJH7-2
BJH7-3
BJH7-10
VSJ6
RDJ6
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199400R0600
1SNA168486R2000
1SNA168487R2100
1SNA168490R0000
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
1
1000
10

12.00
12.00
2.00
0.50
0.80
3.00
0.10
7.50

1SNC167052S0201

1

PAGE 149

HD6/9.5G Quick connect terminal blocks
Feed-through - 9 mm 0.354 in spacing
Description

6 mm²

1SNC167107V0014–– Connection by 5 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in,–– Possibility of testing and transverse connection,–– Use of jumper bars requires to cut out the precut partition,–– NF F 61-017 designation: BC0009-3G2G (1SNA160621R0200).

Ordering details
DescriptionColor
1 circuit5 tabsType
HD6/9.5G

Beige

Main technical data
Connecting capacity

Part Numbers
1SNA160621R0200

Quick-connect:
6.3 x 0.8 mm

44.5
1.75"

V DC

Rated current
Rated cross section

37
1.46"

33.5 1.32"

Rated voltage V AC

Weight(1 pce) g

25

13.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 380 V(Cat. C) 450 V
26 A
6 mm²

380 V
380 V
20 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.60
1.00
1.40
1.80
3.80
2.00

HD6/9.5G

1 conductor
per clamp

Pkg
qty

0.34 … 6 mm²(Cat. C) 400 V(Cat. C) 250 V
25 A
6 mm²

61.5 2.42"

9 mm 0.354 in spacing

CE

RoHS

EAC

5

Accessories
1

Description

2
1

3

4

5

6

2
3

4
5

Beige
Beige

Black

White

BAM2
BAH24
FEHD1
BJH9-2
BJH9-3
BJH9-4BJH9-5
BJH9-10
FC2
VSJ6
RDJ6
RC510

1SNA296351R0000
1SNA168355R1300
1SNA199400R0600
1SNA168460R1100
1SNA168461R0600
1SNA168462R0700
1SNA168463R0000
1SNA168357R1500
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA231000R0700

0.10
5.20

1SNC167074S0201

6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 polesTest plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/9.3G.2G Quick connect terminal blocks
Feed-through - 9 mm 0.354 in spacing
Description

6 mm²

1SNC167004F0014–– 2 circuits: 1 circuit with 3 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of testing and transverse connection and 1 circuit with 2 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x
0.031 in, marked in red,–– Use of jumper bars requires to cut out the precut partition,–– NF F 61-017 designation: BK0009-3Ge/2G (1SNA160563R0000).

Ordering details
DescriptionColor
2 circuits

5 tabsType
HD6/9.3G.2G

Beige

Main technical data
Connecting capacity

HD6/9.3G.2G

1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

9 mm 0.354 in spacing

CE

RoHS

Part Numbers
1SNA160563R0000

Pkg

Weightqty(1 pce) g

25

13.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 380 V(Cat. C) 450 V
26 A
6 mm²

380 V
380 V
20 A

Rail

Type 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²(Cat. C) 400 V(Cat. C) 250 V
25 A
6 mm²

EAC

5

Accessories
Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 polesTest plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

Black

White

Type
BAM2
BAH24
FEHD1
BJH9-2
BJH9-3
BJH9-4BJH9-5
BJH9-10
FC2
VSJ6
RDJ6
RC510

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199400R0600
1SNA168460R1100
1SNA168461R0600
1SNA168462R0700
1SNA168463R0000
1SNA168357R1500
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA231000R0700

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.60
1.00
1.40
1.80
3.80
2.00
0.10
5.20

1SNC167077S0201

1

PAGE 151

HD6/9.2G.3G Quick connect terminal blocks
Feed-through - 9 mm 0.354 in spacing
Description

6 mm²

1SNC167005F0014–– 2 circuits: 1 circuit with 3 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, marked in red
and 1 circuit with 2 vertical tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of testing andtransverse connection,–– Use of jumper bars requires to cut out the precut partition,–– NF F 61-017 designation: BK0009-3G/2Ge (1SNA160564R0100).

Ordering details
DescriptionColor
2 circuits

5 tabsType
HD6/9.2G.3G

Beige

Main technical data
Connecting capacity

HD6/9.2G.3G

1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

9 mm 0.354 in spacing

CE

RoHS

Part Numbers
1SNA160564R0100

Pkg

Weightqty(1 pce) g

25

13.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 380 V(Cat. C) 450 V
26 A
6 mm²

380 V
380 V
20 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.60
1.00
1.40
1.80
3.80
2.00

0.34 … 6 mm²(Cat. C) 400 V(Cat. C) 250 V
25 A
6 mm²

EAC

5

Accessories
1

Description

2
1

3

4

5

6

2
3

4
5

Beige
Beige

Black

White

BAM2
BAH24
FEHD1
BJH9-2
BJH9-3
BJH9-4BJH9-5
BJH9-10
FC2
VSJ6
RDJ6
RC510

1SNA296351R0000
1SNA168355R1300
1SNA199400R0600
1SNA168460R1100
1SNA168461R0600
1SNA168462R0700
1SNA168463R0000
1SNA168357R1500
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA231000R0700

0.10
5.20

1SNC167023S0201

6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 polesTest plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/22.F12G stud terminal blocks
Feed-through - 22 mm 0.866 in spacing
35 mm²

Description–– 115 A main circuit: 1 stud terminal M6 x 31.5 mm 1.24 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer,–– Branch by 12 tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in: 16 A maximum per tab,–– NF F 61-017 designation: BF0025-1F12G.

1SNC167089V0014

Ordering details
DescriptionColor

1 stud M6 and 12 tabs

1 circuit

TypePart Numbers

HD6/22.F12G

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
1.5 ... 35 mm²
Lug (DIN 46235 / 46234)
2.5 ... 35 mm²0.34 … 2.5 mm²
Quick-connect:
6.3 x 0.8 mm
400 V
Rated voltage V AC
V DC
500 V
Rated current
115/16 A
Rated cross section
35 mm²5
0.20"

Weight(1 pce) g

10

55.00

Mounting instructions
NF C

Wire size

HD6/22.F12G

1SNA400782R0000

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 10 mm
Ø 0.394 in

Torque5.3 N.m
46.9 lb.in

61.2 2.41"

53.7 2.12"

50.2 1.98"

M6

CE

RoHS

EAC

50 1.97"22 mm 0.866 in spacing
5

Accessories
Description

2
1

3

4

2
3
4

Color

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inCircuit separators 1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Transparent
Beige

5
5

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJH501
SCH8
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA199411R1400
1SNA199412R1500
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
25
1
10
1
10
1
10

12.00
10.00
6.50
4.80
25.00
25.00
10.00
12.00
7.50

1SNC167036S0201

1

PAGE 153

HD6/30.F12G stud terminal blocks
Feed-through - 30 mm 1.18 in spacing
Description

35 mm²–– 155 A main circuit: 1 stud terminal M6 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer,–– Branch by 12 tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in: 16 A maximum per tab,–– NF F 61-017 designation: BF31.2-1F12G (1SNA295015R1200 + SCH8).

1SNC167106V0014

Ordering details
DescriptionColor

1 stud M6 and 12 tabs

1 cirrcuit

TypePart Numbers

HD6/30.F12G

Beige

Main technical data
Connecting capacity

10

42.00

DIN

NF F 61-017

Lug (NF C 20-130)
1.5 ... 35 mm²
Lug (DIN 46235 / 46234)
2.5 ... 35 mm²0.34 … 6 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V (Cat. C) 750 V 380 V
Rated voltage V AC
V DC(Cat. C) 750 V (Cat. C) 900 V 500 V
Rated current
155/16 A
Rated cross section
35 mm²

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 10 mm
Ø 0.394 in

Torque5.3 N.m
46.9 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
50
25
25
1
10
1
10
1
10

12.00
10.00
6.50
4.80
25.00
25.00
10.00

60 2.36"

49 1.93"52.5 2.07"

Weight(1 pce) g

Mounting instructions
NF C

Wire size

HD6/30.F12G

1SNA295015R1200

Pkg
qty

CE

RoHS

EAC

50 1.97"

30 mm 1.18 in spacing

5

Accessories
1

Description

2
1

3

4

2
3
4

Color

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inCircuit separators 1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Transparent
Beige

5

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

BAM2
BAH22
FJH501
SCH8
CPM
CPM
RTC
PEFH
RPED
RC610

1SNA296351R0000
1SNA164655R0400
1SNA199411R1400
1SNA199412R1500
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

12.00
7.50

1SNC167065S0201

5

Terminal block
markers

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/14.SF Quick connect terminal blocks
For 5x20 fuse - 14 mm 0.551 in spacing
Description

6 mm²–– Terminal block for 5x20 fuse,–– Connection by 2 tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in on each side.

Ordering details

1SNC167151F0014

Description
2 tabs on each
side

Type
HD6/14.SF.2G.2G

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

HD6/14.SF

Color

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CEPart Numbers
1SNA162315R2500

Pkg

Weightqty(1 pce) g

10

17.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²(Cat. C) 500 V(Cat. C) 500 V
25 A
6 mm²

RoHS

(Cat. C) 500 V(Cat. C) 600 V
26 A
6 mm²

EAC

14 mm 0.551 in spacing

5

Accessories
Description

2
1

3

4

2
3
4

10 mm
10.7 mm
End sections
1.6 mmCircuit separators 1.2 mm
Terminal block markers Blank card
End stops

Color
0.394 in
0.421 in
0.063 in
0.047 in

Beige
Beige
Beige
White

Type
BAM2
BAH24
FEH9
SCH8
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA198549R0500
1SNA199412R1500
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
10
25
10

12.00
12.00
4.30
4.80
7.50

1SNC167073S0201

1

PAGE 155

HD6/24.DH Quick connect terminal blocks
Component holder - 24 mm 0.945 in spacing
Description

6 mm²–– Terminal block for screw and solder diodes type SKN5 or SKNa4,–– Connection by 6 or 8 tabs for quick disconnects 6.3 x 0.8 mm 0.248 x 0.031 in,–– NF F 61-017 designation: BG25.2-2G2G (HD6/24.DH + SCH8).

Ordering details
1SNC167092V0014

DescriptionColor

6 tabs8 tabsMain technical data
1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CEPart Numbers
1SNA399964R0600
1SNA399963R0500

Pkg

Weightqty(1 pce) g

10
10

20.00
20.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 250 V(Cat. C) 250 V
26 A
6 mm²

250 V
250 V
16 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
25
25
10
1
10

12.00
12.00
6.50
4.80

0.34 … 6 mm²(Cat. C) 400 V(Cat. C) 250 V
25 A
6 mm²

RoHS

EAC

24 mm 0.945 in spacing

Accessories
1

Description

2
1

3

4

2
3
4

10 mm
0.394 in10.7 mm0.421 inEnd sections
1.5 mm
0.059 inCircuit separators 1.2 mm
0.047 inTerminal block
Label holder
markers
Blank label for PEFH
Blank card
End stops

Beige
Beige
Beige

White

BAM2
BAH24
FJH501
SCH8
PEFH
RPED
RC610

1SNA296351R0000
1SNA168355R1300
1SNA199411R1400
1SNA199412R1500
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

12.00
7.50

1SNC167007S0201

5

HD6/24.DHHD6/24.DH

Beige
Beige

Connecting capacity

HD6/24.DH

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/14.DH Quick connect terminal blocks
Component holder - 14 mm 0.551 in spacing
Description

6 mm²–– Terminal block for screw and solder diodes type SKN2.5 or SKNa2,–– Connection by 2 tabs for quick disconnects 6.3 x 0.8 mm 0.248 x 0.031 in on each side,–– NF F 61-017 designation: BG0014-2G2G (1SNA162971R2700).

1SNC167022F0014

Ordering details
DescriptionColor

2 tabs on each
side

Type
HD6/14.DH

Beige

Main technical data
Connecting capacity
HD6/14.DH

1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

40 1.57"
32.5 1.28"

29 1.14"13.512"

Rated voltage V AC
V DC

Rated current
Rated cross section

54 2.12"

CEPart Numbers
1SNA162971R2700

Pkg

Weightqty(1 pce) g

10

20.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 500 V(Cat. C) 600 V
26 A
6 mm²

380 V
500 V
12 A

Rail

Type 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²(Cat. C) 500 V(Cat. C) 500 V
25 A
6 mm²

RoHS

EAC

14 mm 0.551 in spacing

5

Accessories
Description

2
1

3

4

2
3
4

10 mm
10.7 mm
End sections
1.6 mmCircuit separators 1.2 mm
Terminal block markers Blank card
End stops

Color
0.394 in
0.421 in
0.063 in
0.047 in

Beige
Beige
Beige
White

Type
BAM2
BAH24
FEH9
SCH8
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA198549R0500
1SNA199412R1500
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
10
25
10

12.00
12.00
4.30
4.80
7.50

1SNC167018S0201

1

PAGE 157

HD6/14.DG Quick connect terminal blocks
Component holder - 14 mm 0.551 in spacing
Description

6 mm²–– Terminal block for solder diodes or resistors,–– Connection by 2 tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in on each side,–– NF F 61-017 designation: BG0014-2G2G (1SNA162309R1000).

Ordering details
1SNC167091V0014

DescriptionColor

2 tabs on eachside

Main technical data
1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
Rated current
Rated cross section

44.5 1.75"

52 2.05"

V DC

41 1.61"

HD6/14.DG

Beige

Connecting capacity

HD6/14.DG

Type

CE

Part Numbers
1SNA162309R1000

Pkg

Weightqty(1 pce) g

10

20.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 500 V(Cat. C) 600 V
26 A
6 mm²

380 V
500 V
12 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
25
25
10

12.00
12.00
4.30
4.80
7.50

0.34 … 6 mm²(Cat. C) 500 V(Cat. C) 500 V
25 A
6 mm²

RoHS

EAC

54 2.12"14 mm 0.551 in spacing

5

Accessories
1

Description

2
1
4

2
3
4

0.394 in
0.421 in0.059 in
0.047 in

Beige
Beige
Beige
White

BAM2
BAH24
FEH8
SCH8
RC610

1SNA296351R0000
1SNA168355R1300
1SNA198729R0100
1SNA199412R1500
1SNA233000R0100

1SNC167020S0201

3

10 mm
10.7 mm
End sections
1.5 mmCircuit separators 1.2 mm
Terminal block markers Blank card
End stops

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/9.SDH.1 Quick connect terminal blocks
Component holder - 9.2 mm 0.362 in spacing
6 mm²

Description–– Connection interruptible by plugs for solder components DIA 7 mm 0.287 in max,–– Connection by 2 tabs for quick disconnects 6.3 x 0.8 mm 0.248 x 0.031 in on each side,–– NF F 61-017 designation: BH09.2-2G2G (1SNA162309R1000).

Ordering details
Description

Color

Type

Part Numbers

Pkg

1SNC167090V0014

qty

4 tabsHD6/9.SDH.1

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²
380 V
500 V
16 A

V DC

Rated current
Rated cross section

25

Mounting instructions
NF C

Rated voltage V AC

HD6/9.SDH.1

1SNA400800R0000

Weight(1 pce) g

6 mm²

CE

RoHS

EAC

63.3 2.49"

52.3 2.05"

55.8 2.19"

44.1 1.73"

48.3 1.9"

50 1.96"

25 0.98"

9.2 mm 0.362 in spacing

5

Accessories
Description

2
1

3

4

2
3
4

10 mm
10.7 mm
End sections
1.5 mmCircuit separators 1.2 mm
Terminal block markers Blank card
End stops

Color
0.394 in
0.421 in0.059 in
0.047 in

Beige
Beige
Beige
White

Type
BAM2
BAH24
FESDH
SCH8
RC810

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA400799R0000
1SNA199412R1500
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
10
25
10

12.00
12.00
4.80
8.20

1SNC167051S0201

1

PAGE 159

HD6/14.SDH.1 Quick connect terminal blocks
Component holder - 14 mm 0.551 in spacing
6 mm²

Description–– Connection interruptible by plugs for solder components,–– Connection by 2 tabs for quick disconnects 6.3 x 0.8 mm 0.248 x 0.031 in on each side,–– NF F 61-017 designation: BH0014-2G2G (1SNA162988R2100).

Ordering details
1SNC167008F0014

DescriptionColor

2 tabs on eachside

HD6/14.SDH.1

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

HD6/14.SDH.1

Type

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CEPart Numbers
1SNA162988R2100

Pkg

Weightqty(1 pce) g

10

30.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 500 V(Cat. C) 600 V
26 A
6 mm²

380 V
500 V
16 A

Color

Type

Rail

Type 2, TH 35-7.5,
TH 35-15

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
10
25
10

12.00
12.00
4.30
4.80
7.50

0.34 … 6 mm²(Cat. C) 500 V(Cat. C) 500 V
25 A
6 mm²

RoHS

EAC

14 mm 0.551 in spacing
5

Accessories
1

Description

2
1
4

2
3
4

0.394 in
0.421 in
0.063 in
0.047 in

Beige
Beige
Beige
White

BAM2
BAH24
FEH9
SCH8
RC610

1SNA296351R0000
1SNA168355R1300
1SNA198549R0500
1SNA199412R1500
1SNA233000R0100

1SNC167068S0201

3

10 mm
10.7 mm
End sections
1.6 mmCircuit separators 1.2 mm
Terminal block markers Blank card
End stops

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD6/14.SDH Quick connect terminal blocks
Component holder - 14 mm 0.551 in spacing
6 mm²

Description–– Terminal block for screw and solder diodes type SKN2.5 or SKNa2,–– Connection by 2 tabs for quick disconnects 6.3 x 0.8 mm 0.248 x 0.031 in on each side,–– NF F 61-017 designation: BH0014-2G2G (1SNA162972R2000).

Ordering details
1SNC167105V0014

DescriptionColor

2 tabs on eachside

HD6/14.SDH

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

HD6/14.SDH

Type

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CEPart Numbers
1SNA162972R2000

Pkg

Weightqty(1 pce) g

10

30.00

Mounting instructions
NF C

DIN

NF F 61-017(Cat. C) 500 V(Cat. C) 600 V
26 A
6 mm²

380 V
500 V
16 A

Rail

Type 2, TH 35-7.5,
TH 35-15

0.34 … 6 mm²(Cat. C) 500 V(Cat. C) 500 V
25 A
6 mm²

RoHS

EAC

14 mm 0.551 in spacing
5

Accessories
Description

2
1

3

4

2
3
4

10 mm
10.7 mm
End sections
1.6 mmCircuit separators 1.2 mm
Terminal block markers Blank card
End stops

Color
0.394 in
0.421 in
0.063 in
0.047 in

Beige
Beige
Beige
White

Type
BAM2
BAH24
FEH9
SCH8
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA198549R0500
1SNA199412R1500
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
10
25
10

12.00
12.00
4.30
4.80
7.50

1SNC167069S0201

1

PAGE 161

HD2.5/6.3.3G.3G.1 Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– Connection by 6 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in,–– Possibility of testing and transverse connection,–– Use of jumper bars requires to cut out the precut partition.

Ordering details
1SNC167012F0014

DescriptionColor
1 circuit6 tabsConnecting capacity
Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers
1SNA190316R2700

Pkg

Weightqty(1 pce) g

50

11.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

TypePart Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.80
1.80
1.80
1.80
2.00
2.00

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²(Cat. C) 250 V(Cat. C) 300 V

EAC

6 mm 0.236 in spacing

Accessories
1

Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

Black

White

BAM2
BAH24
FEHD2
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
FC2
VSJ6
RDJ6
RC610

1SNA296351R0000
1SNA168355R1300
1SNA168949R1700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

0.10
7.50

1SNC167046S0201

5

HD2.5/6.3.3G.3G.1

Beige

Main technical data
1 conductor
per clamp

HD2.5/6.3.3G.3G.1

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD2.5/6.3.2G.2G.1.GG Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– 2 circuits: 1 circuit with 4 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of
testing and transverse connection and 1 circuit with 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm
0.248 x 0.031 in,–– Use of jumper bars requires to cut out the precut partition.

1SNC167150F0014

Ordering details
DescriptionColor
2 crcuits

6 tabs1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers

HD2.5/6.3.2G.2G.1.GG 1SNA190312R2300

Red

Main technical data
Connecting capacity

HD2.5/6.3.2G.2G.1.GG

Type

Pkg

Weightqty(1 pce) g

50

10.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²(Cat. C) 250 V(Cat. C) 300 V

EAC

56 mm 0.236 in spacing

Accessories
Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

Black

White

Type
BAM2
BAH24
FEHD2
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
FC2
VSJ6
RDJ6
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA168949R1700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.80
1.80
1.80
1.80
2.00
2.00
0.10
7.50

1SNC167048S0201

1

PAGE 163

HD2.5/6.3.GG1.2G.2G Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– 2 circuits: 1 circuit with 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of
testing and transverse connection and 1 circuit with 4 longitudinal tabs for quick-connect 6.3 x 0.8 mm
0.248 x 0.031 in,–– Use of jumper bars requires to cut out the precut partition.

1SNC167027F0014

Ordering details
DescriptionColor
2 circuits

6 tabs1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

Pkg

Weightqty(1 pce) g

50

11.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

TypePart Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.80
1.80
1.80
1.80
2.00
2.00

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²(Cat. C) 250 V(Cat. C) 300 V
2.5 mm²

EAC

6 mm 0.236 in spacing

Accessories
1

Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

Black

White

BAM2
BAH24
FEHD2
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
FC2
VSJ6
RDJ6
RC610

1SNA296351R0000
1SNA168355R1300
1SNA168949R1700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

0.10
7.50

1SNC167067S0201

5

RoHS

Part Numbers

HD2.5/6.3.GG1.2G.2G 1SNA190314R2500

Red

Main technical data
Connecting capacity

HD2.5/6.3.GG1.2G.2G

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD2.5/6.3.GG.1.2GG Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– 3 circuits: 1 circuit with 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in, possibility of
testing and transverse connection and 2 circuit with 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm
0.248 x 0.031 in,–– Use of jumper bars requires to cut out the precut partition.

1SNC167144F0014

Ordering details
DescriptionColor
3 circuits

6 tabs1 conductor
per clamp

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers

HD2.5/6.3.GG.1.2GG 1SNA199025R1400

Green

Main technical data
Connecting capacity

HD2.5/6.3.GG.1.2GG

Type

Pkg

Weightqty(1 pce) g

50

11.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²(Cat. C) 250 V(Cat. C) 300 V

EAC

56 mm 0.236 in spacing

Accessories
Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

Black

White

Type
BAM2
BAH24
FEHD2
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
FC2
VSJ6
RDJ6
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA168949R1700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.80
1.80
1.80
1.80
2.00
2.00
0.10
7.50

1SNC167060S0201

1

PAGE 165

HD2.5/6.3.2G.2G.1 Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– Connection by 4 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in,–– Possibility of testing and transverse connection,–– Use of jumper bars requires to cut out the precut partition.

Ordering details
1SNC167145F0014

DescriptionColor
1 circuit4 tabsConnecting capacity
Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CE

RoHS

Part Numbers
1SNA190305R0500

Pkg

Weightqty(1 pce) g

50

10.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

TypePart Numbers

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
100
1
1000
10

12.00
12.00
2.00
1.80
1.80
1.80
1.80
2.00
2.00

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²(Cat. C) 250 V(Cat. C) 300 V

EAC

6 mm 0.236 in spacing

Accessories
1

Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
0.394 in10.7 mm0.421 inEnd sections
1 mm
0.039 inJumper bars
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
Test plugs
DIA 2 mm 0.079 in
Fastening kits
Screw M2.5X5 for jumper bar BJH
Washer for screw VSJ
Terminal block markers Blank card
End stops

Color
Beige
Beige

Black

White

BAM2
BAH24
FEHD2
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
FC2
VSJ6
RDJ6
RC610

1SNA296351R0000
1SNA168355R1300
1SNA168949R1700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA007865R2600
1SNA167735R2700
1SNA173241R0600
1SNA233000R0100

0.10
7.50

1SNC167049S0201

5

HD2.5/6.3.2G.2G.1

Beige

Main technical data
1 conductor
per clamp

HD2.5/6.3.2G.2G.1

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD2.5/6.3.GH.2G.H Quick connect terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– 2 circuits: 1 circuit with 1 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in and 1 pin forsoldered connection, and 1 circuit with 2 longitudinal tabs for quick-connect 6.3 x 0.8 mm 0.248 x 0.031 in
and 1 pin for soldered connection.

Ordering details
1SNC167146F0014

DescriptionColor
2 circuits

3 tabs and 2
pins

HD2.5/6.3.GH.2G.H

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

HD2.5/6.3.GH.2G.H

Type

Quick-connect:
6.3 x 0.8 mm

Rated voltage V AC
V DC

Rated current
Rated cross section

CEPart Numbers
1SNA199096R1400

Pkg

Weightqty(1 pce) g

50

11.00

Mounting instructions
NF C

DIN

NF F 61-017

RailType 2, TH 35-7.5,
TH 35-15

0.34 … 2.5 mm²(Cat. C) 250 V(Cat. C) 250 V
25 A
2.5 mm²

RoHS(Cat. C) 250 V(Cat. C) 300 V

EAC

56 mm 0.236 in spacing

Accessories
Description

2
1

3

2
3

10 mm
10.7 mm
End sections
1 mm
Terminal block markers Blank card
End stops

Color
0.394 in
0.421 in
0.039 in

Beige
Beige
White

Type
BAM2
BAH24
FEHD2
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA168949R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10

12.00
12.00
2.00
7.50

1SNC167045S0201

1

PAGE 167

6

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
Stud technology

Technologies presentation				170
Overview					172

10 mm²35 mm²70 mm²120 mm²
185 mm²

HD4/9.F4
HD4/9.F4.2
HD4/10.F4.19
HD10/12.F5.3
HD10/12.F5
HD10/12.F5.1
HD10/12.F5.2
HD35/16.F6.19
HD35/16.F6.19.1
HD70/22.F8.31
HD70/22.F8.31.1
HD70/22.F8.31.2
HD120/30.F10.31
HD120/30.F10.31.1
HD185/36.F12.31.1

2 studs for TH35 & type 2 rails mounting
4 mm²
HD4/9.FF4
6 mm²
HD6/13.FF4
10 mm²
HD10/12.FF5
16 mm²
HD16/14.FF5.21.3
HD16/14.FF5.20.3
HD16/14.FF5.21
HD16/14.FF5.20
2 studs for TH35 & base mounting
35 mm² / 1 AWG
D35/27.FF
70 mm² / 000 AWG D70/32.FF
120 mm² / 300 Kcmil D120/42.FF
185 mm² / 500 Kcmil D185/55.FF
300 mm² / 1000 Kcmil D300/55.FF
2 studs with captive nuts
2.5 mm² / 14 AWG
RGW2.5-V0
6 mm² / 10 AWG
RGW6-V025 mm² / 4 AWG
RGW25-M5-V0
25 mm² / 4 AWG
RGW25-M6-V0

176
		177
M4 stud with self locking nut + TREP washers		
178
M5 stud with self locking nut + spring washers
179
M5 stud with self locking nut + TREP washers		
180
M5 stud with 2 nuts + spring washers		181M5 stud with 2 brass nuts + spring washers		
181
M6 stud with self locking nut + TREP washers		
182
M6 stud with 2 nuts + spring washers		
183
M8 stud with self locking nut + TREP washers
184
M8 stud with 2 nuts + spring washers
185
M8 stud with 2 brass nuts + spring washers		
185
M10 stud with self locking nut + TREP washers
186
M10 stud with 2 nuts + spring washers		
187
M12 stud with 2 nuts + spring washers		
188
M4 stud with self locking nut + spring washers
M4 stud with nut

M4 studs with self locking nut + spring washers
M4 studs with self locking nut + spring washers
M5 studs with self locking nut + TREP washers
M5 studs with self locking nut + spring washers
M5 studs with self locking nut + spring washers
M5 studs with self locking nut + TREP washers
M5 studs with self locking nut + TREP washers

M6 studs with 2 nuts + spring washers		
M8 studs with 2 nuts + spring washers		
M10 studs with 2 nuts + spring washers		
M12 studs with 2 nuts + spring washers		
M16 studs with 2 nuts + spring washers		

M3 studs feed-through with captive nuts		
M4 studs feed-through with captive nuts		
M5 studs feed-through with captive nuts		
M6 studs feed-through with captive nuts		

189
190
191
192
193
194
195

196
197
198
199
200

6

201
202
203
204

Summary_6

1 stud4 mm²

PAGE 169

Railway applications, terminal blocks
Stud technology

The “Pull-out proof” connection
for rolling stock
The stud technology allows all power distribution configurations
and improves wiring secureness thanks to “Pull-out proof"
connection (stud+lug).
The HD terminal blocks provides a large scope of 1 and 2 studs
configurations with different types of washers and nuts
(Onduflex ®, Trep ®, Grover ®).
The D type power blocks provide an alternative with specificlocking foot and rotative covers.
The RGW terminal blocks offer a combination of fast andsecured wiring, with captive nuts in a pivoting wing.

Reliable in harsh conditions
Continuous operation guaranteed for rolling stock–– Environmental tests: aging, corrosion, flammability, toxicity(I2F2, V0, HL3 R22)–– Mechanical tests: vibration and shock.
6

Safety and protection
Secured wiring–– Captive wire connection: stud + ring lug–– Anti-vibration and anti-loosening equipments: self locking
nuts, spring washers.

More control in smaller space
High density wiring with compact design

1SNC167095S0201–– 2 studs version: up to 4 conductors per block–– Compact 1 stud version for 2 conductors.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSFeatures
HD / D typeMultiple connection
technics

RGW type
1

3

Safety wing withcaptive nut
6

Self-locking system

2

Vibration proof
connection

Universal
mounting footEasy 3 step wiring :Open the safety wing - 2 Hook the wire on the stud and close the wing - 3 Screw down the nut
1SNC167095S0201

1

PAGE 171Railway applications, terminal blocks
Stud technology
Range overview up to 300 mm² / 1 000 Kcmil

HD type
From 4 mm² (M4)
to 185 mm² (M12)6

Rotative coverProtects the metallic parts

Spacers
Provide sufficient space between
neighboring terminal blocks

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Anti-loosening equipments
Self-locking nut, plastic elastic washer
or conical spring washers maintaining
a constant pressure on the contact

D type
From 4 mm² (M4)
to 16 mm² (M5)

RGW type
From 2.5 mm² (M3)
to 25 mm² (M6)

Wiring time saving
45% faster than open styletechnology thanks to thesafety wing with captive nut
Easy locking / unlocking on the rail
Locking: single push on side footUnlocking: quarter-turn on the center

Adaptable protective cover
Removable and rotating
for easier wiring

PAGE 173

1SNC167096S0201

6

Railway applications, terminal blocks
Stud technology

HD type - 1 Stud for TH35 & type 2 rails mounting
Section
4 mm²

M4

10 mm²M5

35 mm²M6

70 mm²M8

HD4/9.F4
HD4/9.F4.2
HD4/10.F4.19
HD10/12.F5
HD10/12.F5.1…5.2
HD10/12.F5.3
HD35/16.F6.19
HD35/16.F6.19.1
HD70/22.F8.31
HD70/22.F8.31.1
HD70/22.F8.31.2

120 mm²

HD120/30.F10.31
HD120/30.F10.31.1

185 mm²

HD185/36.F12.31.1

6

HD type - 2 Studs for TH35 & type 2 rails mounting
Section
4 mm²
6 mm²
10 mm²16 mm²

M4
M4
M5
M5

Clamp -

HD4/9.FF4
HD6/13.FF4
HD10/12.FF5
HD16/14.FF5.21

Channels for jumpering or testing -Test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Blown-fuse indicator

HD16/14.FF5.21.3

HD16/14.FF5.20.3

HD16/14.FF5.20

D type - 2 Studs for TH35
Section
35 mm²70 mm²120 mm²
185 mm²
300 mm²

M6
M8
M10
M12
M16

D35/27.FF
D70/32.FF
D120/42.FF
D185/55.FF
D300/55.FF

6

RGW type - 2 Studs with captive nuts for TH35
Section
M3
M4
M5
M6

RGW2.5-V0
RGW6-V0
RGW25-M5-V0
RGW25-M6-V0

1SNC167097S0201

2.5 mm²
6 mm²
25 mm²

PAGE 175HD4/9.F4 stud terminal blocks
Feed-through - 9.5 mm 0.374 in spacing
Description

4 mm²–– 1 stud terminal M4 x 11.5 mm 0.453 in,–– Equipment: self locking nut + spring washer + washer.

Ordering details
1SNC167103V0014

DescriptionColor

1 stud M4

Type

Part Numbers

HD4/9.F4

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 4 mm²
Lug (DIN 46235 / 46234)
0.5 ... 4 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
32 A
Rated cross section
4 mm²

CE

RoHS

Weight(1 pce) g

100

6.00

Mounting instructions
NF C

Wire size

HD4/9.F4

1SNA295391R2000

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 7 mmØ 0.276 in

Torque1.2 N.m
10.6 lb.in

EAC

9.5 mm 0.374 in spacing

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories
1

Description

2
1

3

5

4

6

2
3
4
5
6

Color

10 mm
0.394 in
7.1 mm0.28 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

White

White

BAM2
BAH21
FJHD32
BJH105
SCHD1
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA167489R2200
1SNA295431R1000
1SNA163503R2400
1SNA295428R2500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
1
10
1
10
1
10

12.00
8.00
4.00
197.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167064S0201

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD4/9.F4.2 stud terminal blocks
Feed-through - 9.5 mm 0.374 in spacing
Description

4 mm²–– 1 stud terminal M4 x 11.5 mm 0.453 in,–– Equipment: 1 bottom nut + 2 washers + 1 spring washer + 1 top nut.

Ordering details
1SNC167109V0014

Description

Color
Brass equipment

1 stud M4

Type

Part Numbers

HD4/9.F4.2
HD4/9.F4.2

Yellow
Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Wire sizeCE

9.5 mm 0.374 in spacing

Weight(1 pce) g

100
100

6.00
6.00

Mounting instructions
NF C

Lug (NF C 20-130)
0.5 ... 4 mm²
Lug (DIN 46235 / 46234)
0.5 ... 4 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
32 A
Rated cross section
4 mm²

HD4/9.F4.2

1SNA205392R0700
1SNA295392R2100

Pkg
qty

RoHS

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 7 mmØ 0.276 in

Torque1.2 N.m
10.6 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories

3

Description

2

Color

1

End stops2

End sections

3
4

Jumper bars
10 polesCircuit separators 1.2 mm

0.047 inYellow

5

Spacers

1.2 mm

0.047 inYellow

6

Protecting covers Length 500 mm 19.70 in

7

Terminal block
markers4

10 mm
7.1 mm
1.5 mm

0.394 in
0.28 in0.059 in

Beige
Yellow
Beige

Beige

5

6

Beige
Transparent
Beige

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH21
FJHD32
FJHD32
BJH105
SCHD1
SCHD1
INHD1
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA167489R2200
1SNA205431R2600
1SNA295431R1000
1SNA163503R2400
1SNA205428R0300
1SNA295428R2500
1SNA205427R2200
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
25
10
25
25
25
25
1
10
1
10
1
10

12.00
8.00
4.00
197.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167044S0201

1

PAGE 177

HD4/10.F4.19 stud terminal blocks
Feed-through - 10.5 mm 0.413 in spacing
Description

4 mm²–– 1 stud terminal M4 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer.

Ordering details

1SNC167108V0014

DescriptionColor

1 stud M4

Type

Part Numbers

HD4/10.F4.19

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 4 mm²
Lug (DIN 46235 / 46234)
0.5 ... 4 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
32 A
Rated cross section
4 mm²

CE

RoHS

Weight(1 pce) g

50

11.00

Mounting instructions
NF C

Wire size

HD4/10.F4.19

1SNA295298R0300

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 7 mmØ 0.276 in

Torque1.5 N.m
13.3 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
50
25
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
4.00
2.00
2.00
25.00
25.00
10.00

EAC

10.5 mm 0.413 in spacing

6

Accessories
1

Description

2
1

3

4

2
3
4
5

6

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inCircuit separators 1.5 mm
0.059 in
1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

6

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJHD40
FJDHD
SCHD2
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

1SNA296351R0000
1SNA164655R0400
1SNA295424R1100
1SNA295426R1300
1SNA295429R2600
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

12.00
7.50

1SNC167043S0201

5

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD10/12.F5.3 stud terminal blocks
Feed-through - 12 mm 0.473 in spacing
Description

10 mm²–– 1 stud terminal M5 x 19.5 mm 0.768 in,–– Equipment: self locking nut + spring washer + washer,–– NF F 61-017 designation: BD13.2-1F5 (1SNA295011R1600 + SCHD2).

Ordering details
1SNC167097V0014

DescriptionColor

1 stud M5

TypePart Numbers

HD10/12.F5.3

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 10 mm²
Lug (DIN 46235 / 46234)
0.5 ... 10 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
750 V
Rated voltage V AC
V DC(Cat. C) 750 V
750 V
Rated current
57 A
51 A
Rated cross section
10 mm²CE

12 mm 0.473 in spacing

RoHS

Weight(1 pce) g

50

12.00

Mounting instructions
NF C

Wire size

HD10/12.F5.3

1SNA295011R1600

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories
Description

2
1

3

5

4

6

2
3
4
5
6

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.5 mm
0.059 in
1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7
7

Color

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJHD40
BJH131-10
FJDHD
SCHD2
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA295424R1100
1SNA163468R0000
1SNA295426R1300
1SNA295429R2600
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
59.00
4.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167061S0201

1

PAGE 179

HD10/12.F5 stud terminal blocks
Feed-through - 12 mm 0.473 in spacing
Description

10 mm²–– 1 stud terminal M5 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer.

Ordering details

1SNC167021F0014

DescriptionColor

1 stud M5

TypePart Numbers

HD10/12.F5

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 10 mm²
Lug (DIN 46235 / 46234)
0.5 ... 10 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
57 A
Rated cross section
10 mm²CE

12 mm 0.473 in spacing

6

RoHS

Weight(1 pce) g

50

11.00

Mounting instructions
NF C

Wire size

HD10/12.F5

1SNA295394R2300

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

Accessories
1

Description

2
1

3

5

4

6

2
3
4
5
6

Color

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.5 mm
0.059 in
1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

White

White

BAM2
BAH22
FJHD40
BJH131-10
FJDHD
SCHD2
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA295424R1100
1SNA163468R0000
1SNA295426R1300
1SNA295429R2600
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
59.00
4.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167034S0201

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD10/12.F5 stud terminal blocks
Feed-through - 12 mm 0.473 in spacing
Description

10 mm²–– 1 stud terminal M5 x 19.5 mm 0.768 in,–– Equipment: 1 bottom nut + 2 washers + 1 spring washer + 1 top nut.

Ordering details

1SNC167032F0014

Description

Color
Steel equipment
Brass equipment

1 stud M5

TypePart Numbers

HD10/12.F5.1
HD10/12.F5.2
HD10/12.F5.2

Beige
Beige
Yellow

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 10 mm²
Lug (DIN 46235 / 46234)
0.5 ... 10 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
57 A
Rated cross section
10 mm²

CE

Weight(1 pce) g

50
50
50

11.00
11.00
11.00

Mounting instructions
NF C

Wire size

HD10/12.F5

1SNA295395R2400
1SNA295396R2500
1SNA205396R0300

Pkg
qty

RoHS

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2 N.m17.7 lb.in

EAC

12 mm 0.473 in spacing

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories

3

5

Description

2
1

End stops2

End sections

3
4

Jumper bars
10 polesCircuit separators 1.5 mm
1.2 mm

0.059 in
0.047 inYellow

1.2 mm

0.047 inYellow

4

6

Color
10 mm
8.2 mm
1.5 mm

0.394 in
0.323 in0.059 in

Beige
Yellow
Beige
Beige
Beige

5

Spacers

6

Protecting covers Length 500 mm 19.70 in

7

Terminal block
markers

Beige
Transparent
Beige

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJHD40FJHD40
BJH131-10
FJDHD
SCHD2
SCHD2
INHD1
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA205424R2700
1SNA295424R1100
1SNA163468R0000
1SNA295426R1300
1SNA205429R0400
1SNA295429R2600
1SNA205427R2200
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
25
10
25
25
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
59.00
4.00
2.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167029S0201

1

PAGE 181

HD35/16.F6.19 stud terminal blocks
Feed-through - 16 mm 0.63 in spacing
Description

35 mm²–– 1 stud terminal M6 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer,–– NF F 61-017 designation: BD17.2-1F6 (1SNA295398R0700 + SCHD2).

1SNC167102V0014

Ordering details
DescriptionColor

1 stud M6

TypePart Numbers

HD35/16.F6.19

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
1.5 ... 35 mm²
Lug (DIN 46235 / 46234)
2.5 ... 35 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
750 V
Rated voltage V AC
V DC(Cat. C) 750 V
750 V
Rated current
125 A
125 A
Rated cross section
35 mm²

CE

RoHS

Weight(1 pce) g

50

17.00

Mounting instructions
NF C

Wire size

HD35/16.F6.19

1SNA295398R0700

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 10 mm
Ø 0.394 in

Torque5.3 N.m
46.9 lb.in

EAC

16 mm 0.63 in spacing

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories
1

Description

2
1

3

5

4

6

2
3
4
5
6

Color

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.5 mm
0.059 in
1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

White

White

BAM2
BAH22
FJHD40
BJH17
FJDHD
SCHD2
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA295424R1100
1SNA163475R2700
1SNA295426R1300
1SNA295429R2600
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
99.00
4.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167027S0201

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD35/16.F6.19.1 stud terminal blocks
Feed-through - 16 mm 0.63 in spacing
Description

35 mm²–– 1 stud terminal M6 x 19.5 mm 0.768 in,–– Equipment: 1 bottom nut + 2 washers + 1 spring washer + 1 top nut.

Ordering details
1SNC167038F0014

DescriptionColor

1 stud M6

TypePart Numbers

HD35/16.F6.19.1

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
1.5 ... 35 mm²
Lug (DIN 46235 / 46234)
2.5 ... 35 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
125 A
Rated cross section
35 mm²CE

16 mm 0.63 in spacing

RoHS

Weight(1 pce) g

50

17.00

Mounting instructions
NF C

Wire size

HD35/16.F6.19.1

1SNA295399R0000

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 10 mm
Ø 0.394 in

Torque3 N.m26.6 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories
Description

2
1

3

5

4

6

2
3
4
5
6

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.5 mm
0.059 in
1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7
7

Color

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJHD40
BJH17
FJDHD
SCHD2
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA295424R1100
1SNA163475R2700
1SNA295426R1300
1SNA295429R2600
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
99.00
4.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167056S0201

1

PAGE 183

HD70/22.F8 stud terminal blocks
Feed-through - 22 mm 0.866 in spacing
70 mm²

Description–– 1 stud terminal M8 x 31.5 mm 1.24 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer,–– NF F 61-017 designation: BD23.2-1F8 (1SNA295400R0600 + SCH8).

Ordering details
1SNC167111V0014

DescriptionColor

1 stud M8

TypePart Numbers

HD70/22.F8.31

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
1.5 ... 70 mm²
Lug (DIN 46235 / 46234)
2.5 ... 50 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
750 V
Rated voltage V AC
V DC(Cat. C) 750 V
750 V
Rated current
192 A
188 A
Rated cross section
70 mm²
57,5 2.26”

64 2.52”
68,5 2.69”

31,5

1.24”

50 1.968”

53,5 2.106”
61 2.401”

M8

CE

RoHS

Weight(1 pce) g

50

39.00

Mounting instructions
NF C

Wire size

HD70/22.F8

1SNA295400R0600

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 13 mm
Ø 0.512 in

Torque13.4 N.m
118.6 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

50
1.97”

22 mm 0.866 in spacing

6

Accessories
1

Description

2
1

3

5

4

6

2
3
4
5
6

Color

10 mm
0.394 in10.7 mm0.421 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

White

White

BAM2
BAH24
FJH501
BJH23-10
SCH8
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199411R1400
1SNA163476R2000
1SNA199412R1500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
1
10
1
10
1
10

12.00
12.00
6.50
185.00
4.80
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167028S0201

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD70/22.F8.31 stud terminal blocks
Feed-through - 22 mm 0.866 in spacing
70 mm²

Description–– 1 stud terminal M8 x 31.5 mm 1.24 in,–– Equipment: 1 bottom nut + 2 washers + 1 spring washer + 1 top nut.

Ordering details

1SNC167031F0014

Description

Color
Steel equipment
Brass equipment

1 stud M8

TypePart Numbers

HD70/22.F8.31.1
HD70/22.F8.31.2

Beige
Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
1.5 ... 70 mm²
Lug (DIN 46235 / 46234)
2.5 ... 50 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
192 A
Rated cross section
70 mm²

57,5 2.26”

64 2.52”
68,5 2.69”

31,5

1.24”

50 1.968”

53,5 2.106”
61 2.401”

M8

CE

RoHS

Weight(1 pce) g

50
50

39.00
39.00

Mounting instructions
NF C

Wire size

HD70/22.F8.31

1SNA295401R2300
1SNA295402R2400

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 13 mm
Ø 0.512 in

Torque6 N.m53.1 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

50
1.97”

22 mm 0.866 in spacing

6

Accessories
Description

2
1

3

5

7

4

6

2
3
4
5
6

Color

10 mm
0.394 in10.7 mm0.421 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH24
FJH501
BJH23-10
SCH8
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199411R1400
1SNA163476R2000
1SNA199412R1500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
1
10
1
10
1
10

12.00
12.00
6.50
185.00
4.80
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167039S0201

1

PAGE 185

HD120/30.F10.31 stud terminal blocks
Feed-through - 30 mm 1.18 in spacing
120 mm²

Description–– 1 stud terminal M10 x 31.5 mm 1.24 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer.

Ordering details

1SNC167099V0014

DescriptionColor

1 stud M10

TypePart Numbers

HD120/30.F10.31

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
10 ... 120 mm²
Lug (DIN 46235 / 46234)
6 ... 120 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
269 A
Rated cross section
120 mm²

57,5 2.26”

61 2.40”
68,5 2.69”

31,5

1.24”

50 1.968”

53,5 2.106”
61 2.401”

M10

CE

RoHS

Weight(1 pce) g

10

60.00

Mounting instructions
NF C

Wire size

HD120/30.F10.31

1SNA295448R0100

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 16 mm
Ø 0.63 inTorque30 N.m265.5 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.
50
1.97”

30 mm 1.18 in spacing

6

Accessories
1

Description

2
1

3

5

4

6

2
3
4
5
6

Color

10 mm
0.394 in10.7 mm0.421 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

White

White

BAM2
BAH24
FJH501
BJH311
SCH8
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199411R1400
1SNA163479R0300
1SNA199412R1500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
1
10
1
10
1
10

12.00
12.00
6.50
233.00
4.80
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167055S0201

7

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD120/30.F10.31.1 stud terminal blocks
Feed-through - 30 mm 1.18 in spacing
120 mm²

Description–– 1 stud terminal M10 x 31.5 mm 1.24 in,–– Equipment: 1 bottom nut + 2 washers + 1 spring washer + 1 top nut.

Ordering details

1SNC167112V0014

DescriptionColor

1 stud M10

TypePart Numbers

Beige

HD120/30.F10.31.1

DIN

NF F 61-017

Main technical data
Connecting capacity

Lug (NF C 20-130)
10 ... 120 mm²
Lug (DIN 46235 / 46234)
6 ... 120 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
269 A
Rated cross section
120 mm²

57,5 2.26”

61 2.40”
68,5 2.69”

31,5

1.24”

50 1.968”

53,5 2.106”
61 2.401”

M10

CE

RoHS

Weight(1 pce) g

10

60.00

Mounting instructions
NF C

Wire size

HD120/30.F10.31.1

1SNA295403R2500

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 16 mm
Ø 0.63 inTorque10 N.m
88.5 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.
50
1.97”

30 mm 1.18 in spacing

6

Accessories
Description

2
1

3

5

7

4

6

2
3
4
5
6

Color

10 mm
0.394 in10.7 mm0.421 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH24
FJH501
BJH311
SCH8
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA168355R1300
1SNA199411R1400
1SNA163479R0300
1SNA199412R1500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
1
10
1
10
1
10

12.00
12.00
6.50
233.00
4.80
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167059S0201

1

PAGE 187

HD185/36.F12.31.1 stud terminal blocks
Feed-through - 36 mm 1.42 in spacing
185 mm²

Description–– 1 stud terminal M12 x 31.5 mm 1.24 in,–– Equipment: 1 bottom nut + 2 washers + 1 spring washer + 1 top nut.

Ordering details

1SNC167088V0014

DescriptionColor

1 stud M12

TypePart Numbers

Beige

HD185/36.F12.31.1

DIN

NF F 61-017

Main technical data
Connecting capacity

Lug (NF C 20-130)
35 ... 185 mm²
Lug (DIN 46235 / 46234)
10 ... 150 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
353 A
Rated cross section
185 mm²

57,5 2.26”

61 2.145”
68,5 2.69”

31,5

1.24”

50 1.968”

53,5 2.106”
61 2.401”

M12

CE

RoHS

Weight(1 pce) g

10

79.00

Mounting instructions
NF C

Wire size

HD185/36.F12.31.1

1SNA295405R2700

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 18 mm
Ø 0.709 in

Torque14 N.m123.9 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
50
25
25
25
1
10
1
10
1
10

12.00
12.00
6.50
4.80
2.00
25.00
25.00
10.00

EAC

50
1.97”

36 mm 1.42 in spacing

6

Accessories
1

Description

2
1

3

4

2
3
4
5

Color

10 mm
0.394 in10.7 mm0.421 inEnd sections
1.5 mm
0.059 inCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

6

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

BAM2
BAH24
FJH501
SCH8
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

1SNA296351R0000
1SNA168355R1300
1SNA199411R1400
1SNA199412R1500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

12.00
7.50

1SNC167035S0201

5

6

Type

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD4/9.FF4 stud terminal blocks
Feed-through - 9.5 mm 0.374 in spacing
Description

4 mm²–– 2 stud terminals M4 x 11 mm 0.433 in,–– Equipment: self locking nut + spring washer + washer.

Ordering details
1SNC167110V0014

DescriptionColor

2 studs M4

Type

Part Numbers

HD4/9.FF4

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 4 mm²
Lug (DIN 46235 / 46234)
0.5 ... 4 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
32 A
Rated cross section
4 mm²

CE

RoHS

Weight(1 pce) g

100

6.00

Mounting instructions
NF C

Wire size

HD4/9.FF4

1SNA295393R2200

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 7 mmØ 0.276 in

Torque1.2 N.m
10.6 lb.in

EAC

9.5 mm 0.374 in spacing

6

Accessories
Description

2
1

3

5

7

4

6

2
3
4
5
6

Color

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJHD32
BJH105
SCHD1
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA295431R1000
1SNA163503R2400
1SNA295428R2500
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
1
10
1
10
1
10

12.00
10.00
4.00
197.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167066S0201

1

PAGE 189

HD6/13.FF4 stud terminal blocks
Feed-through - 13 mm 0.512 in spacing
Description

6 mm²–– 2 stud terminals M4 x 15 mm 0.531 in,–– Equipment: self locking nut + spring washer + washer,–– NF F 61-017 designation: BE0013-FF4 (1SNA295014R1100).

Ordering details
1SNC167104V0014

DescriptionColor

2 studs M4Main technical data
Connecting capacity

21 0.83"

15 0.59"

25.2 0.99"

CE

RoHS

1SNA295014R1100

Pkg

Weightqty(1 pce) g

10

15.00

Mounting instructions
NF C

Lug (NF C 20-130)
0.5 ... 6 mm²
Lug (DIN 46235 / 46234)
Quick-connect:
6.3 x 0.8 mm(Cat. C) 400 V
Rated voltage V AC
V DC(Cat. C) 250 V
Rated current
51 A
Rated cross section
6 mm²

19 0.75"

Part Numbers

HD6/13.FF4

Beige

Wire size

HD6/13.FF4

Type

Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 7 mmØ 0.276 in(Cat. C) 380 V 380 V(Cat. C) 450 V 380 V
47 A
51 A

Torque1.2 N.m
10.6 lb.in

Color

Part Numbers

Pkg

Weightqty(1 pce) g

50
50
25
10
25
1

12.00
8.00
4.30
10.00
4.80
20.00

DIN

NF F 61-017

0.5 ... 6 mm²

Rail

EAC

40 1.57"

13 mm 0.512 in spacing

6

Accessories
1

Description

2
1

3

4

2
3
4
5

10 mm
0.394 in
7.1 mm0.28 inEnd sections
1.5 mm
0.059 inJumper bars
10 poles
125 A (IEC)
Circuit separators 1.2 mm
0.047 inTerminal block markers Precut blank label
End stops

Beige
Beige
Beige
White

Type
BAM2
BAH21
FEH8
BJS13-10
SCH8REH3

1SNA296351R0000
1SNA167489R2200
1SNA198729R0100
1SNA167224R2700
1SNA199412R1500
1SNA163155R2600

1SNC167040S0201

5

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD10/12.FF5 stud terminal blocks
Feed-through - 12 mm 0.473 in spacing
Description

10 mm²–– 2 stud terminals M5 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer.

Ordering details

1SNC167098V0014

DescriptionColor

2 studs M5

Type

Part Numbers

HD10/12.FF5

Beige

Main technical data
Connecting capacity

DIN

NF F 61-017

Lug (NF C 20-130)
0.5 ... 10 mm²
Lug (DIN 46235 / 46234)
0.5 ... 10 mm²
Quick-connect:
6.3 x 0.8 mm(Cat. C) 750 V
Rated voltage V AC
V DC(Cat. C) 750 V
Rated current
57 A
Rated cross section
10 mm²CE

12 mm 0.473 in spacing

RoHS

Weight(1 pce) g

50

11.00

Mounting instructions
NF C

Wire size

HD10/12.FF5

1SNA295397R2600

Pkg
qty

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories
Description

2
1

3

5

4

6

2
3
4
5
6

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
10 polesCircuit separators 1.5 mm
0.059 in
1.2 mm
0.047 inSpacers
1.2 mm
0.047 inProtecting covers Length 500 mm 19.70 in
End stops

Beige
Beige
Beige
Beige
Transparent
Beige

7
7

Color

Terminal block
markers

Blank strip label for CPM
Label holder
Blank label for PEFH
Blank card

White

White

Type
BAM2
BAH22
FJHD50
BJH131-10
FJDHD
SCHD5
INHD1
CPM
CPM
RTC
PEFH
RPED
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA295425R1200
1SNA163468R0000
1SNA295426R1300
1SNA295430R2300
1SNA295427R1400
1SNA187312R1400
1SNA197312R1600
1SNA163156R2700
1SNA163497R1600
1SNA163518R2200
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10
25
25
25
1
10
1
10
1
10

12.00
10.00
4.00
59.00
4.00
2.00
2.00
25.00
25.00
10.00
12.00
7.50

1SNC167057S0201

1

PAGE 191

HD16/14.FF5.21.3 stud terminal blocks
Feed-through - 14 mm 0.551 in spacing
Description

16 mm²

1SNC167020F0014–– 2 stud terminals M5 x 19.5 mm 0.768 in,–– Equipment: self locking nut + spring washer + washer,–– 18 mm 0.709 in spacing adding SCH6 or INH3,–– Two jumpering options: 14 mm 0.551 in spacing with BJH14 and 18 mm 0.709 in spacing (adding INH3)
with BJH18,–– NF F 61-017 designation: BE0018-FF5 (1SNA295012R1700 + SCH6 or INH3).

Ordering details
DescriptionColor

2 studs M5

Type

Part Numbers

HD16/14.FF5.21.3

Beige

Main technical data
Connecting capacity

HD16/14.FF5.21.3

Lug (NF C 20-130)
0.5 ... 16 mm²
Lug (DIN 46235 / 46234)
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
71 A
Rated cross section
16 mm²

CE

Weight(1 pce) g

25

24.00

Mounting instructions
NF C

Wire size

14 mm 0.551 in spacing

1SNA295012R1700

Pkg
qty

RoHS

DIN

NF F 61-017

0.5 ... 16 mm²(Cat. C) 500 V 380 V(Cat. C) 600 V 500 V
65 A
71 A

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

6

Accessories
1

Description

2
1

3

4

5

6

2
3

Beige
Beige

Beige
Beige
White

Type
BAM2
BAH22
FEH8
BJH14-2
BJH14-3
BJH14-4
BJH14-5
BJH14-10
BJH18-2
BJH18-3
BJH18-4
BJH18-5
BJH18-10
SCH6
INH3
REH3
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA198729R0100
1SNA173438R2400
1SNA173439R2500
1SNA173441R2700
1SNA173449R0700
1SNA173451R2100
1SNA173452R2200
1SNA173453R2300
1SNA173454R2400
1SNA173460R0600
1SNA173461R2300
1SNA199393R2200
1SNA199394R2300
1SNA163155R2600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
1
10
10
10
1
1
1
1
1
1
20
25
1
10

12.00
10.00
4.30
5.30
8.30
11.20
14.20
28.00
6.20
9.90
13.80
17.50
36.90
2.60
20.00
7.50

1SNC167042S0201

4
5
6

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 poles2 poles
3 poles
4 poles
5 poles
10 polesCircuit separators 4 mm
0.157 inSpacers
4 mm
0.157 inTerminal block
Precut blank label
markers
Blank card
End stops

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD16/14.FF5.20.3 stud terminal blocks
Feed-through - 14 mm 0.551 in spacing
Description

16 mm²–– 2 stud terminals M5 x 19.5 mm 0.768 in,–– Equipment: self locking nut + spring washer + washer,–– NF F 61-017 designation: BE0014-FF5 (1SNA295013R1000).

Ordering details
1SNC167100V0014

DescriptionColor

2 studs M5

Part Numbers

HD16/14.FF5.20.3

Beige

Main technical data
Connecting capacity

Lug (NF C 20-130)
0.5 ... 16 mm²
Lug (DIN 46235 / 46234)
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
71 A
Rated cross section
16 mm²

CE

1SNA295013R1000

Pkg

Weightqty(1 pce) g

25

26.00

Mounting instructions
NF C

Wire size

HD16/14.FF5.20.3

Type

RoHS

DIN

NF F 61-017

0.5 ... 16 mm²(Cat. C) 500 V 380 V(Cat. C) 600 V 500 V
65 A
51 A

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

14 mm 0.551 in spacing

6

Accessories
Description

2
1

3

2
3

10 mm
8.2 mmEnd sections
1.5 mmTerminal block markers Blank card
End stops

Color
0.394 in
0.323 in0.059 in

Beige
Beige
White

Type
BAM2
BAH22
FEH8
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA198729R0100
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
10

12.00
10.00
4.30
7.50

1SNC167063S0201

1

PAGE 193

HD16/14.FF5.21 stud terminal blocks
Feed-through - 14 mm 0.551 in spacing
Description

16 mm²

1SNC167009F0014–– 2 stud terminals M5 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer,–– 18 mm 0.709 in spacing adding SCH6 or INH3,–– Two jumpering options: 14 mm 0.551 in spacing with BJH14 and 18 mm 0.709 in spacing (adding INH3)
with BJH18.

Ordering details
DescriptionColor

2 studs M5

Type

Part Numbers

HD16/14.FF5.21

Beige

Main technical data
Connecting capacity
HD16/14.FF5.21

Lug (NF C 20-130)
0.5 ... 16 mm²
Lug (DIN 46235 / 46234)
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
71 A
Rated cross section
16 mm²14 mm 0.551 in spacing

6

Weight(1 pce) g

25

30.00

Mounting instructions
NF C

Wire size

CE

1SNA162991R1400

Pkg
qty

RoHS

DIN

NF F 61-017

0.5 ... 16 mm²(Cat. C) 500 V(Cat. C) 600 V
65 A

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

The use of a jumper bar requires to use a spacer instead of a circuit separator.

Accessories
1

Description

2
1

3

4

5

6

2
3

Beige
Beige

Beige
Beige
White

Type
BAM2
BAH22
FEH8
BJH14-2
BJH14-3
BJH14-4
BJH14-5
BJH14-10
BJH18-2
BJH18-3
BJH18-4
BJH18-5
BJH18-10
SCH6
INH3
REH3
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA198729R0100
1SNA173438R2400
1SNA173439R2500
1SNA173441R2700
1SNA173449R0700
1SNA173451R2100
1SNA173452R2200
1SNA173453R2300
1SNA173454R2400
1SNA173460R0600
1SNA173461R2300
1SNA199393R2200
1SNA199394R2300
1SNA163155R2600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
1
10
10
10
1
1
1
1
1
1
20
25
1
10

12.00
10.00
4.30
5.30
8.30
11.20
14.20
28.00
6.20
9.90
13.80
17.50
36.90
2.60
20.00
7.50

1SNC167024S0201

4
5
6

10 mm
0.394 in
8.2 mm0.323 inEnd sections
1.5 mm
0.059 inJumper bars
2 poles
3 poles
4 poles
5 poles
10 poles2 poles
3 poles
4 poles
5 poles
10 polesCircuit separators 4 mm
0.157 inSpacers
4 mm
0.157 inTerminal block
Precut blank label
markers
Blank card
End stops

Color

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSHD16/14.FF5.20 stud terminal blocks
Feed-through - 14 mm 0.551 in spacing
Description

16 mm²–– 2 stud terminals M5 x 19.5 mm 0.768 in,–– Equipment: H 130 self locking nut + TREP 3L washer + washer.

Ordering details

1SNC167007F0014

DescriptionColor

2 studs M5

Part Numbers

HD16/14.FF5.20

Beige

Main technical data
Connecting capacity

Lug (NF C 20-130)
0.5 ... 16 mm²
Lug (DIN 46235 / 46234)
Quick-connect:
6.3 x 0.8 mm(Cat. C) 500 V
Rated voltage V AC
V DC(Cat. C) 500 V
Rated current
71 A
Rated cross section
16 mm²

CE

1SNA162979R0700

Pkg

Weightqty(1 pce) g

25

27.00

Mounting instructions
NF C

Wire size

HD16/14.FF5.20

Type

RoHS

DIN

NF F 61-017

0.5 ... 16 mm²(Cat. C) 500 V 380 V(Cat. C) 600 V 500 V
65 A
51 A

Rail
Tool

Type 2, TH 35-7.5,
TH 35-15
WrenchØ 8 mmØ 0.315 in

Torque2.5 N.m
22.1 lb.in

EAC

14 mm 0.551 in spacing

6

Accessories

3

Description

2
1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
0.394 in
8.2 mm0.323 in
1.5 mm
0.059 inPrecut blank label
Blank card

Beige
Beige
White

Type
BAM2
BAH22
FEH8
REH3
RC610

Part Numbers
1SNA296351R0000
1SNA164655R0400
1SNA198729R0100
1SNA163155R2600
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
25
1
10

12.00
10.00
4.30
20.00
7.50

1SNC167017S0201

1

PAGE 195

D35/27.FF power terminal blocks
Feed-through - 27 mm 1.062 in spacing
Description

35 mm²–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

1 AWG

Ordering details
1SNC165010F0014

Description

Color

Feed-through2 studs M6 without coverD35/27.FF

Grey

1SNA190001R2000

Main technical data

113 4.45"
52 2.05"

DIN

UL
2.5-35 mm² 2.5-50 mm² 1 AWG

CSA

Lugs
Tool

2.5-35 mm² 2.5-35 mm²
C4

UL

Rail

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

TorqueJumper screw
Tool

59 2.32"=

66.5 2.62"

Pkg

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

10

Weight(1 pce) g
130.00

Mounting instructions
NF C

IEC
Screw clamp=

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrules
Gauge

D35/27.FF

Type

IEC

UL

CSA

125 A
35 mm²1000 V
8000 V

125 A
1 AWG
600 V

TorqueTH 35-7.5,
TH 35-15
Wrench
H10 mm
3 - 6 N.m
26.1 - 52 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
Torque56.5 2.22"

Wire stripping
length27 mm 1.062 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

6

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS27-2
BJS27-3
DRF6
CPUF35RC810

1SNK900102R0000
1SNA205772R1300
1SNA205773R1400
1SNA205767R1600
1SNA190016R1600
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
34.00
52.00
4.00
8.30
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165006S0201 - Rev. C

5Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD70/32.FF power terminal blocks
Feed-through - 32 mm 1.260 in spacing
Description

70 mm²000 AWG–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130 and
DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M8 without coverD70/32.FF

Grey

56 2.20"

67 2.64"74.5 2.93"=

70 2.76"

Pkg

DIN

6-95 mm²
6-70 mm²C66-70 mm²
6-70 mm²

UL
000 AWG

CSA

Rail
Lugs
Tool

UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

3

Weight(1 pce) g
269.00

Mounting instructions
NF C

IEC

=

1SNA190002R2100

Main technical data

Screw clamp

140 5.51"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrules
Gauge

D70/32.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

192 A
70 mm²1000 V
8000 V

170 A
000 AWG
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH13 mm
6 - 12 N.m
52 - 104 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
TorqueWire stripping
length32 mm 1.260 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

6

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS32-2
BJS32-3
DRF8
CPUF70RC810

1SNK900102R0000
1SNA205774R1500
1SNA205775R1600
1SNA205768R2700
1SNA190017R1700
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
66.00
105.80
5.00
12.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165005S0201 - Rev. C

5Technical data valid for copper conductors only.

PAGE 197

D120/42.FF power terminal blocks
Feed-through - 42 mm 1.653 in spacing
120 mm²
300 Kcmil

Description–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130 and
DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M10 without
cover

76 2.99"

84 3.31"=70 2.76"

1SNA190003R2200

Main technical data

Screw clamp

64 2.51"=

D120/42.FF

Grey

Pkg

DIN

UL
6-150 mm² 6-120 mm² 300 Kcmil

CSA

Rail
Lugs
Tool

6-120 mm²
C8

UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
423.00

Mounting instructions
NF C

IEC

140 5.51"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrules
Gauge

D120/42.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

269 A
120 mm²
1000 V
8000 V

269 A
300 Kcmil
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH17 mm10 - 20 N.m
87 - 174 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
Torque42 mm 1.653 in spacing

Wire stripping
lengthThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

6

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS42-2
BJS42-3
DRF10
CPUF120RC810

1SNK900102R0000
1SNA205776R1700
1SNA205777R1000
1SNA205769R2000
1SNA190018R2000
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
93.00
153.00
7.00
24.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165004S0201 - Rev. C

5Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSD185/55.FF power terminal blocks
Feed-through - 55 mm 2.165 in spacing
185 mm²
500 Kcmil

Description–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M12 without
cover

90 3.54"97.5 3.84"=

81.5 3.21"

1SNA190004R2300

Main technical data

Screw clamp

71 2.79"=

D185/55.FF

Grey

Pkg

DIN

UL
25-240 mm² 6-185 mm² 500 Kcmil

CSA

Rail
Lugs
Tool

6-185 mm²
C11

UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
615.00

Mounting instructions
NF C

IEC

163 6.42"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrules
Gauge

D185/55.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

353 A
185 mm²
1000 V
8000 V

353 A
500 Kcmil
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH24 mm14 - 30 N.m
123.9 - 265.5 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
TorqueWire stripping
length55 mm 2.165 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

USR CNR

Gost R

6

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS551-2
BJS551-3
DRF12
CPUF185
RC810

1SNK900102R0000
1SNA205778R2100
1SNA205779R2200
1SNA205770R2500
1SNA190019R2100
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
158.00266.00
8.00
40.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165010S0201 - Rev. C

5Technical data valid for copper conductors only.

PAGE 199

D300/55.FF power terminal blocks
Feed-through - 55 mm 2.165 in spacing
300 mm²
1000 Kcmil

Description–– Rated cross section up to 300 mm² / 1000 Kcmil, IP20 protection cover,–– Holding foot on DIN 3 rail with two position for easy mounting, lug mounting in accordance with NF C 20-130
and DIN 46234, various marking options, rail or base mounting.

1SNC165009F0014

Ordering details
Description

Color

Feed-through2 studs M16 without
cover

99 3.89"106.5 4.20"=

81.5 3.21"

1SNA190005R2400

Main technical data

Screw clamp

72 2.83"=

D300/55.FF

Grey

Pkg

DIN

UL
CSA
25-300 mm² 6-300 mm² 1000 Kcmil

Rail6-300 mm²

Lugs
Tool
UL

CSA

Rigid: Solid/Stranded
Flexible without ferrule
Gauge

Bar
Rated current
Rated cross section
Rated voltage
Impulse withstand voltage

1

Weight(1 pce) g
775.00

Mounting instructions
NF C

IEC

163 6.42"

Part Number

qty

Connecting capacity
Rigid: Solid/Stranded
Lugs
Flexible with insulated ferrule
Gauge

D300/55.FF

Type

TorqueJumper screw
Tool

IEC

UL

CSA

520 A
300 mm²
1000 V
8000 V

460 A
1000 Kcmil
600 V

TorqueTH 35-7.5,
TH 35-15
WrenchH24 mm25 - 50 N.m
217 - 435 lb.in
Allen key
6 mm
0.236 in
6 - 12 N.m
52 - 104 lb.in

Screw clamp
Tool
TorqueWire stripping
length55 mm 2.165 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
RoHS

6

USR CNR

Gost R

Accessories
Description
1

2

3

4

Color

Type

Part Number

Pkg
qty

1
2
3
4
5

10 mm
0.394 in
2 poles
3 poles
Splitters
For 6.35x0.8mm faston clips and screws
Protecting covers IP20 rotating protecting cover
Terminal block markers Blank card
End stops
Jumper bars

Dark grey

Grey
White

BAZH1
BJS551-2
BJS551-3
DRF16
CPUF185
RC810

1SNK900102R0000
1SNA205778R2100
1SNA205779R2200
1SNA205771R1200
1SNA190019R2100
1SNA234000R0200

20
5
5
10
2
1

Weight(1 pce) g
24.00
158.00266.00
7.00
40.00
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC165011S0201 - Rev. C

5Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRGW2.5 Ring lug terminal blocks
Feed-through - 9 mm 0.354 in spacing
2.5 mm²
14 AWG

Description–– Stud terminal block for ring lug connection,–– Integrated captive nuts in protective wings provide easy and secured connection,–– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168064V0014

Description
Feed-throughColorWith 2 studs M3 and captive nuts
in wings

54.7 2.15"

1SNA510003R0000

Pkg

Weightqty(1 pce) g

45

11.78

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

IEC
0.1 … 2.5 mm²
0.1 … 2.5 mm²

UL
26 ... 14 AWG

24 A

15 A
20 A
14 AWG

20 A

600 V

600 V

2.5 mm²
300 A
800 V
8000 V
IP10

CSA
26 ... 14 AWG

Rail
Nuts
Tool
Torque14 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 4 mmØ 0.157 in
0.6 ... 0.8 N.m
5.3 ... 7.1 lb.in
7 mm
0.28 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

47.2 1.86"

52 2.05"

RGW2.5-V0

Part Numbers

Mounting instructions

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

44.7 1.76"

Grey

Main technical data
Lugs

RGW2.5Type

22.4 0.88"

9 mm 0.354 in spacing

6

Accessories
Description

2
1
2
3

3

5

4
4
5

Color

End stops
10 mm
0.394 inEnd sections
1.2 mm
0.047 in
Lateral jumper bars 2 poles
24 A (IEC)3 poles
24 A (IEC)4 poles
24 A (IEC)
10 poles24 A (IEC)
Circuit separators 1.5 mm
0.059 inTerminal block
Blank marker
markers

Dark grey
Grey
Orange

Grey
White

Type

Part Numbers

BAM4
1SNK900001R0000
E-RGW2.5
1SNA519003R0000
PC-RG2.5-2
1SNA519103R0200
PC-RG2.5-3
1SNA519103R0300
PC-RG2.5-4
1SNA519103R0400
PC-RG2.5-10
1SNA519103R1000
CS-RGW-S
1SNA519200R0000
M-W610PC
1SNA235511R0600
MG-CPM-01 41090 1SNB041090R0510

Pkg

Weightqty(1 pce) g

50
25
25
20
15
5
25
360
1960

14.00
1.89
3.02
4.69
6.36
16.39
4.59
8.03
0.351

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground Ring lug terminal blocks
Description
GroundColorWith 2 studs M3 and captive
nuts in wings

Green-yellow

Type
RGW2.5-PE-V0

Part Numbers
1SNA511003R0500

Pkg

Weightqty(1 pce) g

45

28.56

Technical data valid for copper conductors only.

PAGE 201

1SNC168024S0201

1

RGW6 Ring lug terminal blocks
Feed-through - 11 mm 0.433 in spacing
6 mm²
10 AWG

Description–– Stud terminal block for ring lug connection,–– Integrated captive nuts in protective wings provide easy and secured connection,–– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168068V0014

Description
Feed-throughWith 2 studs M4 and captive nuts
in wings

Type
Grey

RGW6-V0

Main technical data
Lugs

RGW6

Part Numbers
1SNA510024R0000

Pkg

Weightqty(1 pce) g

40

19.76

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 6 mm²
0.1 … 6 mm²

UL
22 ... 10 AWG

41 A

30 A
30 A
10 AWG

30 A

600 V

600 V

6 mm²
720 A
800 V
8000 V
IP10

CSA
22 ... 10 AWG

Rail
Nuts
Tool
Torque10 AWGMax width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.8 ... 1.2 N.m
7.1 ... 10.6 lb.in
9.4 mm0.37 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

53.5 2.10"

61 2.40"44.7 1.76"

58 2.28"

Color

RoHS

USR CNR

CSA

22.35 0.88"

11 mm 0.433 in spacing

6

Accessories
1

Description

2
1
2
3

3

5

4

4
5

Color

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)7 poles
41 A (IEC)
10 poles
41 A (IEC)
Circuit separators 1.5 mm
0.059 inTerminal block
Blank marker
markers

Dark grey
Grey
Orange

Grey
White

Type

Part Numbers

BAM4
1SNK900001R0000
E-RGW6
1SNA519004R0000
PC-RG6-2
1SNA519104R0200
PC-RG6-3
1SNA519104R0300
PC-RG6-4
1SNA519104R0400
PC-RG6-7
1SNA519104R0700
PC-RG6-10
1SNA519104R1000
CS-RGW-S
1SNA519200R0000
M-W810PC
1SNA235510R0800
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

50
50
25
20
15
5
5
25
260
1120

14.00
2.65
3.44
5.40
7.33
13.24
19.05
4.59
0.27
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description
GroundColorWith 2 studs M4 and captive
nuts in wings

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
RGW6-PE-V0

Part Numbers
1SNA511024R0500

Pkg

Weightqty(1 pce) g

40

31.76

1SNC168016S0201

Ground Ring lug terminal blocks

RGW25-M5 Ring lug terminal blocks
Feed-through - 18 mm 0.709 in spacing
25 mm²
4 AWG

Description–– Stud terminal block for ring lug connection,–– Integrated captive nuts in protective wings provide easy and secured connection,–– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168067V0014

Description
Feed-through71.8 2.83"

Grey

RGW25-M5-V0

Part Numbers
1SNA510005R0000

Pkg

Weightqty(1 pce) g

10

49.10

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 25 mm²
0.1 … 25 mm²

UL
26 ... 4 AWG

101 A

85 A
115 A
4 AWG

100 A

600 V

600 V

25 mm²3000 A
800 V
8000 V
IP10

CSA
26 ... 4 AWG

Rail
Nuts
Tool
Torque

4 AWG
Max width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
3 ... 3.5 N.m
26.5 ...31 lb.in
16.2 mm0.64 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

64.3 2.53"

69 2.72"

60 2.36"

With 2 studs M5 and captive nuts
in wings

Type

Main technical data
Lugs

RGW25-M5

Color

30 1.18"

18 mm 0.709 in spacing

6

Accessories

3

5

Description

2

4

1
2
3
4
5

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
101 A (IEC)
Circuit separators 2 mm
0.079 inTerminal block
Blank marker
markers

Color
Dark grey
Grey
Orange
Grey
White

Type

Part Numbers

BAZH1
1SNK900102R0000
E-RGW25
1SNA519005R0000
PC-RG25-2
1SNA519106R0200
CS-RGW-L
1SNA519201R0000
M-W1010PC
1SNA235512R1000
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

20
25
25
25
200
1120

24.00
0.146
8.81
13.72
0.10
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC168028S0201

1

Technical data valid for copper conductors only.

PAGE 203

RGW25-M6 Ring lug terminal blocks
Feed-through - 18 mm 0.709 in spacing
25 mm²
4 AWG

Description–– Stud terminal block for ring lug connection,–– Integrated captive nuts in protective wings provide easy and secured connection,–– Universal mounting on symmetrical and asymmetrical rails.

Ordering details
1SNC168067V0014

Description
Feed-through71.8 2.83"

Grey

RGW25-M6-V0

Part Numbers
1SNA510006R0000

Pkg

Weightqty(1 pce) g

10

48.44

Mounting instructions

Rigid: Solid/Stranded
Flexible with insulated ferrule
Gauge

Rated current
Maximum current
Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
ProtectionIEC
0.1 … 25 mm²
0.1 … 25 mm²

UL
26 ... 4 AWG

101 A

85 A
115 A
4 AWG

100 A

600 V

600 V

25 mm²3000 A
800 V
8000 V
IP10

CSA
26 ... 4 AWG

Rail
Nuts
Tool
Torque

4 AWG
Max width of lug

G32, TH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
3.2 ... 3.5 N.m
28.3 ...32.7 lb.in
16.2 mm0.64 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

64.3 2.53"

69 2.72"

60 2.36"

With 2 studs M6 and captive nuts
in wings

Type

Main technical data
Lugs

RGW25-M6

Color

30 1.18"

18 mm 0.709 in spacing

6

Accessories
1

3

4

1
2
3
4
5

End stops
10 mm
0.394 inEnd sections
1.4 mm
0.055 in
Lateral jumper bars 2 poles
101 A (IEC)
Circuit separators 2 mm
0.079 inTerminal block
Blank marker
markers

Color
Dark grey
Grey
Orange
Grey
White

Type

Part Numbers

BAZH1
1SNK900102R0000
E-RGW25
1SNA519005R0000
PC-RG25-2
1SNA519106R0200
CS-RGW-L
1SNA519201R0000
M-W1010PC
1SNA235512R1000
MG-CPM-01 41096 1SNB041096R0810

Pkg

Weightqty(1 pce) g

20
25
25
25
200
1120

24.00
0.146
8.81
13.72
0.10
0.400

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC168029S0201

5

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

PB_2

6

PAGE 205

7

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
Screw clamp technology complying with NF F 55251

Technologies presentation				208
Overview					210

E4/6
E6/8
E10/16

Disconnect with push-turn knob
6 mm²
M6/8.STP
ES8-CG

Disconnect with plug
10 mm²
E10/16.S

		
211

		
212

		
213

1/4 turn push-turn knob 			
1/4 turn push-turn knob - contact protected by dust cover

214
215

			
216

7

Summary_7

Feed-through
2.5 mm²
6 mm²
10 mm²

PAGE 207

Railway applications, terminal blocks
Screw clamp technology complying with NF F 55251 and CT448

The proven reliability andperformance for railway
infrastructure
The screw clamp technology complying with NF F 55251
and CT448 minimizes maintenance & trouble shooting
operations thanks to the anti-release system. The screw islocked in total safety.
The high density capacity screw clamp connection can fit up to
two conductors per clamp which offers extended possibilities
in electrical cabinets.
CE

RoHS

EAC

Reliable in harsh conditions


Excellentwithstand in corrosive atmosphere–– Self-cleaning push-turn knob–– Stainless steel screw–– Nickeled copper alloy compression clamp–– Dust protection covering.

Continuous operations

Maintenance and trouble shooting operations are minimized–– Thanks to our anti-release system–– Screw is locked in total safety.

1SNC160250S0201

7

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSFeatures
Focus on ES8-CG
Opened circuit

Closed circuit

Push-turn knob

Contact blade

1/4
turn
2 mm

Contact lyres

Self-cleaning
displacement

Very good circuit stability thanks
to the balanced contact forces7

Switched by a push-turn knob
(1/4 turn) operated witha screwdriver

Corrosion proof
screw clamp

1SNC160250S0201

Black plastic cover providing
dust protection

PAGE 209

Railway applications, terminal blocks
Screw clamp and pluggable technologies

Feed-throughSection
2.5 mm²
6 mm²
10 mm²

E4/6
E6/8
E10/16

Disconnect with plug

Disconnect with push-turn knob
1/4

1/4

Section
6 mm²
10 mm²

M6/8.STP

ES8-CG

E10/16.S

Clamp -

Channels for jumpering or testing -Test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Blown-fuse indicator

1SNC160251S0201

7

E4/6 railway terminal blocks
Feed-through - 6 mm 0.236 in spacing
2.5 mm²

Description–– Ease you test operations with the builtt-in test socket - NF F 55-251 designation: ER 6,–– Sy SNCF 7 963 1088.

Ordering details

1SNC167147F0014

Description
Feed-throughColorWith test socket DIA 2 mm 0.079 in

TypePart Numbers

E4/6

Beige

1SNA190468R0000

Main technical data
Connecting capacity
1 conductor
per clamp

DIN

NF F 55-251

Rated current
Rated cross section

CE

8.00

0.5 … 4 mm²
0.5 … 2.5 mm²

G32

Wire stripping
length

9.5 mm
0.374 in

Tool
V AC
V DC

50

Rail

E4/6

Rated voltage

Weight(1 pce) g

Mounting instructions
NF C

Rigid: Solid/Stranded
Flexible without ferrule

Pkg
qty

500 V
500 V
30 A
2.5 mm²

RoHS

750 V
900 V
26 A
2.5 mm²

500 V
500 V
30 A
2.5 mm²

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.43 - 7.08 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
25
100
25
10

11.00
1.30
2.00
13.00
7.50

EAC

6 mm 0.236 in spacing

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Test plugs
Terminal block
markers

Color
10 mm
0.394 in
1 mm
0.039 in
DIA 2 mm 0.079 inLabel holder
Blank card

Beige
Beige
Black
Black
White

Type
BAR
FEE6-1
FC2
PE
RC610

1SNA164519R2400
1SNA193080R1200
1SNA007865R2600
1SNA103007R2300
1SNA233000R0100

7

1SNC167047S0201

1

PAGE 211

E6/8 railway terminal blocks
Feed-through - 8 mm 0.315 in spacing
6 mm²

Description–– Ease you test operations with the builtt-in test socket - NF F 55-251 designation: ER 8,–– Sy SNCF 7 963 1114.

Ordering details

1SNC167148F0014

Description
Feed-throughColorWith test socket DIA 4 mm 0.157 in

TypePart Numbers

E6/8

Beige

1SNA190607R0400

Main technical data
Connecting capacity
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule

DIN

NF F 55-251

Rated current
Rated cross section

CE

RoHS

50

15.00

0.5 … 10 mm²
0.5 … 6 mm²

Rail

G32

Wire stripping
length13 mm
0.512 in

Tool
V AC
V DC

Weight(1 pce) g

Mounting instructions
NF C

E6/8

Rated voltage

Pkg
qty

500 V
500 V
51 A
6 mm²

750 V
900 V
46 A
6 mm²

500 V
500 V
51 A
6 mm²

Flat screwdriverØ 5 mmØ 0.197 in

Torque0.8 - 1 N.m
7.08 - 8.85 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
25
10
10
10
25
10

11.00
2.00
3.00
14.00
10.00
13.00
8.20

EAC

8 mm 0.315 in spacing

Accessories
1

Description

2
1
2
3

7

3

4
4
5

End stops
10 mm
0.394 inEnd sections
1 mm
0.039 in
Lateral jumper bars 2 poles
50 A (IEC)
10 poles
50 A (IEC)
Test plugs
DIA 4 mm 0.157 in
Terminal block
Label holder
markers
Blank card

Color
Beige
Beige
Black
White
Black
White

Type
BAR
FEE8-2
PC8-2
PC8-10
FC4
PE
RC810

1SNA164519R2400
1SNA193085R0300
1SNA116538R1700
1SNA163313R2400
1SNA167860R0100
1SNA103007R2300
1SNA234000R0200

1SNC167081S0201

5

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSE10/16 railway terminal blocks
Feed-through - 16 mm 0.63 in spacing
Description

10 mm²–– Ease you test operations with the builtt-in test socket - NF F 55-251 designation: ER 16,–– Sy SNCF 7 963 1110.

Ordering details

1SNC167141F0014

Description
Feed-throughColorWith test socket DIA 4 mm 0.157 in

TypePart Numbers

E10/16

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule

1SNA191302R2700

DIN

NF F 55-251

Rated current
Rated cross section

CE

25

47.00

0.5 … 16 mm²
0.5 … 10 mm²

Rail

G32

Wire stripping
length14 mm
0.551 in

Tool
V AC
V DC

Weight(1 pce) g

Mounting instructions
NF C

E10/16

Rated voltage

Pkg
qty

750 V
500 V
71 A
10 mm²

RoHS

750 V
900 V
63 A
10 mm²

500 V
500 V
71 A
10 mm²

Flat screwdriverØ 5.5 mm
Ø 0.217 in

Torque2.5 - 3 N.m
22.1 - 26.6 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
10
10
10
25
10

11.00

EAC

16 mm 0.63 in spacing

Accessories
1

3

Description

2

4

1
2
3
4
5

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 2 poles
Test plugs
DIA 4 mm 0.157 in
Terminal block
Label holder
markers
Blank card

Color
Beige
Beige
White
Black
White

Type
BAR
FEE10-16
PC
FC4PE
RC1010

1SNA164519R2400
1SNA193449R2400
1SNA168497R2300
1SNA167860R0100
1SNA103007R2300
1SNA238000R1600

7.00
10.00
13.00
1.30

7

1SNC167053S0201

5

PAGE 213

M6/8.STP railway terminal blocks
Disconnect with push-turn knob - 8 mm 0.315 in spacing
6 mm²

Description–– Ease your disconnect operations with the disconnect 1/4 turn push-turn knob,–– Possibility to seal in the open position,–– Ease your test operations with the built-in test socket,–– NF F 55-251 designation: ES 8,–– Sy SNCF 7 963 1156.

Ordering details

1SNC167143F0014

1/4

Description
Disconnect

Color
With 2 tests sockets DIA 4 mm
0.157 in

TypePart Numbers

M6/8.STP

Beige

Main technical data
1 conductor
per clamp

NF C

Rigid: Solid/Stranded
Flexible without ferrule

DIN

NF F 55-251

0.5 … 10 mm²
0.5 … 6 mm²

Rail
Wire stripping
lengthTool

60 2.37"52.5 2.07"

57.5 2.27"

55.5 2.19"

Rated voltage

V AC
V DC

500 V
500 V
17 A
6 mm²

Rated current
Rated cross section

25.5 1.00"

CE

30.5 1.20"

RoHS

8 mm 0.315 in spacing

Weight(1 pce) g

25

21.00

Mounting instructions

Connecting capacity
M6/8.STP

1SNA195212R1000

Pkg
qty

500 V
500 V
15 A
6 mm²

500 V
500 V
12 A
6 mm²

TorqueG32, TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 4 mmØ 0.157 in

0.8 - 1 N.m
7.08 - 8.85 lb.in

EAC

A

1

2

A: Closing operation
B: Opening operation
1: Push2: Turn
3: stop

B

1

2
3

3

7

Accessories
1

3

4

6

Color

1

End stops2
3

End sections
2.8 mm0.110 in
Lateral jumper bars 1 poles
24 A (IEC)2 poles
50 A (IEC)
10 poles
50 A (IEC)
Test plugs
DIA 4 mm 0.157 in
Short circuit plugs With test socket DIA 4 mm 0.157 in
Terminal block markers Blank card

4
5
6

10 mm

0.394 in

Beige
Beige
Grey
Black
White
Beige
White

Type
BAM2
BAR
FEMT1
AD2.5
PC8-2
PC8-10FC4
BNSTP1
RC810

Part Numbers
1SNA296351R0000
1SNA164519R2400
1SNA193137R0300
1SNA114205R2000
1SNA116538R1700
1SNA163313R2400
1SNA167860R0100
1SNA196792R1700
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
50
50
10
10
10
20
10

12.00
11.00
2.00
1.60
3.00
14.00
10.00
14.00
8.20

1SNC167026S0201

5

Description

2

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

ES8-CG railway terminal blocks
Disconnect with push-turn knob - 8 mm 0.315 in spacing
6 mm²

1SNC167071F0014

1/4

Description–– Particularly recommanded for corrosive atmosphere: Self-cleaning displacement system and dust protection
with plastic cover,–– Ease and safe your disconnect operations with the disconnect 1/4 turn push-turn knob,–– Possibility to seal in the open position,–– Ease your test operations with the built-in test socket.

Ordering details
Description
Disconnect

Color
With 2 tests sockets DIA 4 mm
0.157 inType
ES8-CG
ES8-CG

Beige
Green

Main technical data
1 conductor
per clamp

1SNA400015R2000
1SNA400014R2700

Rigid: Solid/Stranded
Flexible without ferrule

According to CT 448 of the IG PS 52

Rail

0.5 … 10 mm²
0.5 … 6 mm²

Wire stripping
lengthTool

60 2.37"52.5 2.07"

57.5 2.27"

55.5 2.19"

Rated voltage

V AC
V DC

500 V
500 V
2A
6 mm²

Rated current
Rated cross section

25.5 1.00"

CE

Pkg

Weightqty(1 pce) g

25
25

21.00
21.00

Mounting instructions

Connecting capacity
ES8-CG

Part Numbers

RoHS

TorqueG32, TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverØ 4 mmØ 0.157 in

0.8 - 1 N.m
7.08 - 8.85 lb.in

EAC

30.5 1.20"

8 mm 0.315 in spacing

A

1

2

A: Closing operation
B: Opening operation
1: Push2: Turn
3: stop

B

1

2
3

3

7

Accessories

3

5

Description

2

4

6

Color

1

End stops2
3

End sections
2.8 mm0.110 in
Lateral jumper bars 1 poles
24 A (IEC)2 poles
50 A (IEC)
10 poles
50 A (IEC)
Test plugs
DIA 4 mm 0.157 in
Short circuit plugs With test socket DIA 4 mm 0.157 in
Terminal block markers Blank card

4
5
6

10 mm

0.394 in

Beige
Beige
Grey
Black
White
Beige
White

Type
BAM2
BAR
FEMT1
AD2.5
PC8-2
PC8-10FC4
BNSTP1
RC810

Part Numbers
1SNA296351R0000
1SNA164519R2400
1SNA193137R0300
1SNA114205R2000
1SNA116538R1700
1SNA163313R2400
1SNA167860R0100
1SNA196792R1700
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
50
50
10
10
10
20
10

12.00
11.00
2.00
1.60
3.00
14.00
10.00
14.00
8.20

1SNC167030S0201

1

PAGE 215

E10/16.S railway terminal blocks
Disconnect with plug - 16 mm 0.63 in spacing
Description

10 mm²–– NF F 55-251 designation: ES 16,–– Sy SNCF 7 963 1109

Ordering details

1SNC167142F0014

Description

Color

Disconnect

TypePart Numbers

E10/16.S

Beige

Main technical data
Connecting capacity
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule

1SNA191296R1100

DIN

NF F 55-251

Rated current
Rated cross section

CE

RoHS

25

47.00

0.5 … 16 mm²
0.5 … 10 mm²

Rail

G32

Wire stripping
length14 mm
0.551 in

Tool
V AC
V DC

Weight(1 pce) g

Mounting instructions
NF C

E10/16.S

Rated voltage

Pkg
qty

500 V
500 V

380 V
440 V

10 mm²10 mm²

500 V
500 V
30 A
10 mm²

Flat screwdriverØ 5.5 mm
Ø 0.217 in

Torque2.5 - 3 N.m
22.1 - 26.6 lb.inPart Numbers

Pkg

Weightqty(1 pce) g

50
10
10
25
20
20
20
25
10

11.00

EAC

16 mm 0.63 in spacing

Accessories
1

7

3

4

Description

2

5

6

1
2
3
5
4
6
7

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 2 poles
Guide plugs
Component plugs
With test
Short circuit plugs With test socket DIA 4 mm 0.157 in
Terminal block
Label holder
markers
Blank card

Color
Beige
Beige
Beige
Black
Beige
Black
White

Type
BAR
FEE10-16
PC
BIE
SSB20
SSB20TBNSTP1
PE
RC1010

1SNA164519R2400
1SNA193449R2400
1SNA168497R2300
1SNA196915R0200
1SNA103098R2600
1SNA103099R2700
1SNA196792R1700
1SNA103007R2300
1SNA238000R1600

7.00
36.00
15.00
17.00
14.00
13.00
1.30

1SNC167025S0201

7

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

PB_3

7

PAGE 217

Summary_8

8

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
Screw clamp technology
Technologies presentation			
Overview				

220
224

Feed-through4 mm² / 12 AWG
6 mm² / 10 AWG

ZS4			
228
ZS6			
229
ZS6-3S and ZS6-4S		
with 3 and 4 connections
230-231
10 mm² / 6 AWG
ZS10			23216 mm² / 4 AWG
ZS16			23325 mm² / 3 AWG
ZS25			23435 mm² / 0 AWG
ZS35			23550 mm² / 0 AWG
ZS50			23670 mm² / 00 AWG
ZS70			23795 mm² / 0000 AWG ZS95			
238
150 mm² / 350 Kcmil ZS150			
239
240 mm² / 240 Kcmil ZS240			
240
Ground4 mm² / 12 AWG
6 mm² / 10 AWG

ZS4-PE			ZS6-PE			
ZS6-3S-PE and ZS6-4S-PE
with 3 and 4 connections
10 mm² / 6 AWG
ZS10-PE			
16 mm² / 4 AWG
ZS16-PE			
25 mm² / 3 AWG
ZS25-PE			
35 mm² / 2 AWG
ZS35-PE			
35 mm²
ZS35-PEN		+ neutral
50 mm² / 0 AWG
ZS50-PE			
70 mm² / 00 AWG
ZS70-PE			
95 mm² / 0000 AWG ZS95-PE			

241
242
243-244
245
246
247
248
249
250
251
252

Disconnect with blade
4 mm² / 10 AWG
ZS4-S, ZS4-S-T, ZS4-S-R1 and ZS4-S-T-R1
6 mm² / 10 AWG
ZS6-S and ZS6-S-4S-T
10 mm² / 6 AWG
ZS10-S			

253-256257-258
259

with testwith test

Disconnect with plug
4 mm² / 10 AWG
ZS4-SP, ZS4-SP-T2, ZS4-SP-R1 and ZS4-SP-T2-R1 with test
10 mm² / 6 AWG
ZS10-SP			

260-263264

Fuse and marshalling cabinets application overview		

266

For 5x20 and 5x25 mm fuses
4 mm² / 10 AWG
ZS4-SF1 and ZS4-SF1-T
with test
ZS4-SF1-R		
with fuse indicator and test
ZS4-R1		feed-throughZS4-S-R3		
disconnect with lever268-269
270-271272
273

For 5x20 mm fuses and marshalling cabinets application
4 mm² / 10 AWG
ZS4-SF			
ZS4-SF-T
with test 		ZS4-SF-R
with fuse indicator and test
ZS4-R2feed-throughZS4-PE-R2
ground 		ZS4-S-R2
disconnect with lever274
275
276-277
278
279
280

Double deck
4 mm² / 12 AWG
6 mm² / 10 AWG

281
282
283

ZS4-D2 and ZS4-D1
ZS6-D2 and ZS6-D1
ZS6-D2-PE
ZS6-D1-PE
ZS4-D2-S
ZS4-D2-S-T
ZS4-D2-SF1
ZS4-D2-SF1-R

2 and 1 feed-through circuits
284-285
2 and 1 feed-through circuits
286-287
1 feed-through circuit and 1 ground circuit
288
1 ground circuit
289
1 disconnect circuit and 1 feed-through circuit
290
1 disconnect circuit + test and 1 feed-through circuit
291
1 fuse circuit and 1 feed-through circuit
292
1 fuse circuit + fuse indicator and 1 feed-through circuit
293

Triple deck
4 mm² / 12 AWG
4 mm² / 10 AWG

ZS4-T3ZS4-T3-R1

3 feed-through circuits
3 feed-through circuits

Component holder
4 mm² / 12 AWG

ZS4-D-CH-UD and ZS4-D-CH-DU

4 mm² / 10 AWG

Test and measurement
Overview				
10 mm² / 6 AWG
ZS10-ST			
ZS10-ST-1
for Potential Transformer circuits
ZS10-ST-T4
for Current Transformer circuits
ZS10-R1
feed-throughZS10-PE-R1
ground		

8

294
295
296-297
298
302
303
304
305
306

PAGE 219

Summary_8

For 6.3x32 mm fuses (¼ x 1¼ in)
10 mm² / 6 AWG
ZS10-SF			ZS10-SF-R
with fuse indicator
ZS10-S-R2
disconnect with leverScrew clamp technology - SNK series, terminal blocks
Features and benefits

TE Connectivity screw clamp technology benefits from 60 yearsof experience.

Speed up your projects
An optimized conductor guiding
Smooth connection process up to 2 conductors with orwithout ferrules thanks to funnel entry shape.
Also perfectly adapted to double ferrule shape 1

1Security: flap avoiding the insertion of cable underneath theclamp 2 .

2

Better project identification–– Circuit identification is improved thanks to the 20% larger
marking area–– Pre-mark by hand or with label on our flat marking surface
and start immediately the wiring, before the final markers
mounting–– Spare markers re-printing in case of modifications.
Clear circuit identification

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK161092S0201

Engineered conductor entry

8

Screw clamp technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process.
Mounting, wiring, testing… made easy.
Avoid mounting and wiring errors: asymmetrical design allows
immediate visual check in case of reversed terminal blocks.

Asymmetrical design avoids mounting error

Minimize retightening campaigns
High torque resistance : the clamp is punched to increase thenumber of threads in contact by 30 % 1 .
The TE Connectivity exclusive anti-release system createsa controlled locking-screw effect reinforced by the 2
overlapping tabs that maintain the clamp parts 2 .
1

High torque resistance2

Anti-release system

8

Screwless accessories

Snap-in ground terminal block for
rapid installation

PAGE 221

1SNK161092S0201

Faster accessories mounting
Save up to 70% mounting time thanks to screwless accessories: jumpers, component plugs, test devices, end stops andsnap-in ground terminal blocks.

Screw clamp technology - SNK series, terminal blocks
Features and benefits

Easy to install
Smart design facilitating assembly process.
Mounting, wiring, testing… made easy.
Locking pin 1 allows quick and easy lock up to ten blocks
in position at a time.
Closed jumper location allows great stiffness of the terminal
block, optimal jumper guiding and avoids deflections whiletightening.

1

Lock up to ten blocks in position
at a time

Smart accessories
Flexible test solutions from individual insulated test adapter totest connectors for complete assemblies testing.
–– Direct plug-in into jumpers channels–– 5, 6, 8 mm spacing, mixing various spacing is possible–– 1000 V rating.

Plug-in individual test adapter

Plug-in test connector

Closed jumper location for stiffness

Component holder plugs for series or parallel component
mounting (resistors, filters, diodes..).
Can be installed after wiring.
Series plug offers screwless component connection(no soldering).

Series plug associated withdisconnect blocks

Parallel plug to be installed between
2 blocks

Pre-cut poles easy removableby handPredefined shape to identify
connected poles

8

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK161092S0201

Smart plug-in jumpers:
Pre-cut poles removable by hand: clean cut.
Insulated up to 1000 V (avoid use of separators).
Predefined shapes in molding to easily identify connected
poles with a pen.

Screw clamp technology - SNK series, terminal blocks
Features and benefits

Optimized logistics
Reduce your accessories inventory by up to 50%
SNK PI-Spring, screw and pluggable ranges share the same
accessories.
Reduced packaging adapted to the usage(20 items packaging for some references).

All end sections and circuit separators fit several types
and sizes of blocks.

Stock only one end section for managing your assembly
up to 240 mm²

Shared accessories for SNK PI-Spring, screw and pluggable ranges

Facilitate maintenance operations

Terminals can be individually removed from a terminal
assembly equipped with markers:
TE Connectivity markers become independent after strip
mounting, TE Connectivity markers remain on terminal
in any situation.

Reliable in harsh conditions
Qualified for worldwide markets, applications
and for severe environments: vibration, shock, corrosion…

8

RoHS

CE

EAC

DNV

Rina

1SNK161092S0201

hazlocMaintenance operations facilitated

PAGE 223

SNK series, terminal blocks
Screw clamp technology - Range overview from 4 to 240 mm² – 12 to 500 Kcmil

2

Connections

Single deckFeed-throughGroundDisconnect
Fuse3

Connections

Single deckFeed-throughGround4

Connections

Single deckFeed-throughGroundDisconnect8

Double central
channels
allowsmulticonfigurations(jumpering, testing
and measuring)

Circuit separator
without spacing loss

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Voltage test
screwdriver entry
point accepts
Category II probes

2x2

Connections

Double deckFeed-throughGroundDisconnect
Fuse
Component holder

2

Connections

Test and measurement
Feed-throughGroundDisconnect

3x 2

Connections

Triple deckFeed-through8

End section
can be used
as circuit separator

1SNK161089S0201

Plugcomponent holder

Rotating label
holdereasy plug-in injumper channel

PAGE 225

SNK series, terminal blocks
Screw clamp technology

Feed-throughGroundSection
12 AWG
10 AWG

4 mm²

6 mm²
10 mm²16 mm²25 mm²35 mm²10 AWG
6 AWG
4 AWG
3 AWG
0 AWG
2 AWG
50 mm² 0 AWG
70 mm² 00 AWG
95 mm² 0000 AWG
150 mm² 350 Kcmil
240 mm² 500 Kcmil

ZS4

ZS6
ZS10
ZS16
ZS25

ZS4-PE

ZS6-3S

ZS6-4S

ZS6-PE
ZS10-PE
ZS16-PE
ZS25-PE

ZS6-3S-PE

ZS6-4S-PE

ZS35
ZS35-PE
ZS50-PE
ZS70-PE
ZS95-PE

ZS50
ZS70
ZS95
ZS150
ZS240

Disconnect with blade

Disconnect with plug

Section
4 mm²

10 AWG

ZS4-S

6 mm²
10 mm²10 AWG
6 AWG

ZS6-S
ZS10-SZS4-S-T2ZS4-S-R1

ZS4-S-T2-R1
ZS4-S-T2.3-R1

ZS4-SPZS4-SP-T2

ZS4-SP-R1

ZS4-SP-T2-R1

ZS6-S-4S-T2
ZS10-SP8

For 5 x 20 mm fuses

Alignedfor marshalling cabinets application

For 6.3 x 32 mm fuses(¼ x 1¼ in)

Aligned

ZS10-SF

ZS10-S-R2

Section
10 AWG

10 mm²

6 AWG

Clamp -

ZS4-SFZS4-SF-T2

ZS4-SF-R1
ZS4-SF-R3

Channels for jumpering or testing -ZS4-SF-R2
ZS4-SF-R4

Test socket -INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-R2Blown-fuse indicator

ZS4-PE-R2

ZS4-S-R2
ZS10-SF-R1
ZS10-SF-R3

1SNK161066S0201

4 mm²

Double deckFeed-throughZS4-D2GroundDisconnect
with blade

For 5 x 20 mm
and 5 x 25 mm fuses

ZS4-D1ZS4-D2-S

ZS6-D2

Triple deck

ZS6-D1ZS6-D2-PE

ZS4-D2-S-T2

ZS4-D2-SF1

Component holder

Feed-throughZS4-D-CH-UD ZS4-D-CH-DU

ZS4-T3ZS4-T3-R1

ZS4-D2-SF1-R1
ZS4-D2-SF-R3

ZS6-D1-PE

Test & measurement
Test disconnect with sliding link

ZS10-ST

ZS10-ST-T4
ZS10-ST-1

Aligned with ZS10-ST

ZS10-R1

ZS10-PE-R1

8

ZS4-SF1ZS4-SF1-T2

ZS4-SF1-R1
ZS4-SF1-R3

Feed-throughaligned with ZS4-SF1

ZS4-SF1-R2
ZS4-SF1-R4

ZS4-R1ZS4-S-R3

1SNK161066S0201

For 5 x 20 mm and 5 x 25 mm fuses

PAGE 227

ZS4 screw clamp terminal blocks
Feed-through - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description–– Save space by connecting conductors up to 4 mm² (without insulated ferrule, CB certified) 12 AWG in just
5.2 mm 0.205 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
Description

Color

Feed-through

Grey
Blue
OrangeYellow
GreenRed
Purple
Brown
White
Black

1SNK161001F0014

ZS4

Type
ZS4
ZS4-BLZS4-ORZS4-YLZS4-GNZS4-RDZS4-PRZS4-BRZS4-WHZS4-BK

1SNK505010R0000
1SNK505020R0000
1SNK505030R0000
1SNK505060R0000
1SNK505061R0000
1SNK505062R0000
1SNK505063R0000
1SNK505064R0000
1SNK505065R0000
1SNK505066R0000

Main technical data

5.2 mm 0.205 in spacing

48.8 1.92"

56.3 2.22"
26.7 1.05"

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50
50

8.80
8.80
8.80
8.80
8.80
8.80
8.80
8.80
8.80
8.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 32 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 20 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

53 2.09"

Pkg

Part Number

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
10.5 mm0.412 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

1

Description

2
1
2
3

8

3

4

5

6

7

9

8

10

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
5 Circuit separators 0 mm
0 in
3 mm
0.118 in6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
8 Shield connectors
9 Protecting covers 5.2 mm 0.205 in spacing
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey

Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHBS
1SNK900600R0000
PL5
1SNK900618R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
30
10
10
20
20
20
20
10
10
20
10
1960
22
20
10

14.00
2.20
1.30
2.00
2.70
3.50
7.10
36.00
2.80
0.20
5.20
1.70
2.40
5.20
5.20
3.50
1.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS4

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZS4-PEPart Number
1SNK505150R0000

Pkg

Weightqty(1 pce) g

20

12.10

1SNK161001S0201

Accessories

ZS6 screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description
Save space by connecting conductors up to 6 mm² (without insulated ferrule, CB certified) 10 AWG in just
6 mm 0.236 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
Description

Color

Feed-through

Grey
Blue
OrangeYellow
GreenRed
Purple
Brown
White
Black

1SNK161011F0014

ZS6

Type
ZS6
ZS6-BLZS6-ORZS6-YLZS6-GNZS6-RDZS6-PRZS6-BRZS6-WHZS6-BK

1SNK506010R0000
1SNK506020R0000
1SNK506030R0000
1SNK506060R0000
1SNK506061R0000
1SNK506062R0000
1SNK506063R0000
1SNK506064R0000
1SNK506065R0000
1SNK506066R0000

Main technical data

6 mm 0.236 in spacing

48.8 1.92"

56.3 2.22"
26.7 1.05"

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50
50

10.60
10.60
10.60
10.60
10.60
10.60
10.60
10.60
10.60
10.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
41 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 41 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 30 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

53 2.09"

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
10.5 mm0.412 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

2

CB

RoHS

USR CNRCSAEAC ExATEX

Description
3

5

7

9

11

4

6

8

10

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1
2
3

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
5 Circuit separators 0 mm
0 in
3 mm
0.118 in6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
End module, 5.2 mm 0.205 in
8 Spacers
0.8 mm
0.031 in9 Shield connectors
10 Protecting covers 6 mm 0.236 in spacing
11 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
SHBS
1SNK900600R0000
PL6
1SNK900619R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
20
10
10
20
10
1680
22
20
10

14.00
2.20
1.30
2.10
2.90
3.60
7.40
38.10
2.80
0.20
5.20
1.70
2.40
5.20
0.80
3.50
1.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS6

Green-yellow

Type
ZS6-PEPart Number
1SNK506150R0000

Pkg

Weightqty(1 pce) g

20

13.70

Technical data valid for copper conductors only.

PAGE 229

8

1SNK161008S0201

1

ZS6-3S screw clamp terminal blocks
Feed-through with 3 connections - 6 mm 0.236 in spacing
Description

6 mm²–– Recommended for energy markets and highly demanding applications requiring that only one conductor beconnected per clamp,–– These blocks offer a high density connecting capacity (up to 3 connections) in a low profile and just 6 mm
0.236 in spacing.

10 AWG

1SNK161075V0014

Ordering details
Description

Color

Type

Feed-through

Grey
Blue
Yellow

Part Number

ZS6-3S
ZS6-3S-BL
ZS6-3S-YL

Main technical data
ZS6-3S

6 mm 0.236 in spacing

49.7 1.96"

57.2 2.25"
35.65 1.40"

Weight(1 pce) g

50
50
50

11.80
11.80
11.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
32 A / 4 mm²
39 A / 6 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

550 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 30 A

1 conductor
per clamp
62 2.44"

1SNK506011R0000
1SNK506021R0000
1SNK506067R0000

Pkg
qty

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

800 V
8000 V
IP20

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque100 kA
600 V

TH 35-7.5,
TH 35-15
10.5 mm0.413 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3
4

5

6

7

8

4
5
6
7
8
9

9

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-3S
1SNK505912R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
20
10
10
1680
22
20
10

14.00
2.50
1.30
2.10
2.90
3.60
7.40
38.10
2.80
0.20
5.20
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS6-3S

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZS6-3S-PE

Part Number
1SNK506151R0000

Pkg

Weightqty(1 pce) g

25

16.20

1SNK161067S0201

8

3

Color

ZS6-4S screw clamp terminal blocks
Feed-through with 4 connections - 6 mm 0.236 in spacing
Description

6 mm²–– High density wiring (one potential distribution on 4 independent screw clamps) in a very low profile and just
6 mm 0.236 in spacing,–– Recommended for energy markets and highly demanding applications requiring that only one conductor beconnected per clamp.

10 AWG

1SNK161078V0014

Ordering details
Description

Color

Type

Feed-through

Grey
Blue
Yellow

Part Number

ZS6-4S
ZS6-4S-BL
ZS6-4S-YL

1SNK506012R0000
1SNK506022R0000
1SNK506068R0000

Main technical data
ZS6-4S

6 mm 0.236 in spacing

49.7 1.96"

57.2 2.25"
35.65 1.29"

Weight(1 pce) g

50
50
50

15.00
15.00
15.00

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
32 A / 4 mm²
39 A / 6 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

550 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 30 A

1 conductor
per clamp
72.7 2.86"

Pkg
qty

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

800 V
8000 V
IP20

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque100 kA
600 V

TH 35-7.5,
TH 35-15
10.5 mm0.413 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
Description

2
1
2
3

3

4

5

6

7

8

4
5
6
7
8
9

9

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
50 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB6-50
1SNK906350R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
10
10
20
20
20
20
10
10
1680
22
20
10

14.00
3.10
1.30
2.10
2.90
3.60
7.40
38.10
2.80
0.20
5.20
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS6-4S

Green-yellow

Type
ZS6-4S-PE

Part Number
1SNK506152R0000

Pkg

Weightqty(1 pce) g

25

19.40

Technical data valid for copper conductors only.

PAGE 231

1SNK161068S0201

1

ZS10 screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Save space by connecting conductors up to 10 mm² (without insulated ferrule, CB certified) 6 AWG in just
8 mm 0.315 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
Description

Color

Feed-through

Grey
Blue
OrangeYellow
GreenRed
Purple
Brown
White
Black

1SNK161008F0014

ZS10

Type
ZS10
ZS10-BL
ZS10-ORZS10-YL
ZS10-GN
ZS10-RD
ZS10-PR
ZS10-BR
ZS10-WH
ZS10-BK

Main technical data
53 2.09"48.8 1.92"

56.3 2.22"

8 mm 0.315 in spacing

1SNK508010R0000
1SNK508020R0000
1SNK508030R0000
1SNK508060R0000
1SNK508061R0000
1SNK508062R0000
1SNK508063R0000
1SNK508064R0000
1SNK508065R0000
1SNK508066R0000

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50
50

14.10
14.10
14.10
14.10
14.10
14.10
14.10
14.10
14.10
14.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
57 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 57 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 42 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

26.7 1.05"

Pkg

Part Number

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Flat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
42 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
12 mm
0.472 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

1

Description

2
1
2
3

8

3

4

5

6

7

9

8

10

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)
4 Cross spacing jumpers 3 poles
32 A (IEC)
5 Circuit separators 0 mm
0 in
3 mm
0.118 in6 Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
7 Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
8 Spacers
2.8 mm0.110 in
9 Protecting covers 8 mm 0.315 in spacing
10 Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
PL8
1SNK900620R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
40
20
10
20
20
20
20
10
10
10
10
1680
22
20
10

14.00
2.20
2.70
4.10
5.60
7.00
14.20
2.80
0.20
5.20
1.70
2.40
5.20
5.20
1.40
2.60
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS10

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZS10-PEPart Number
1SNK508150R0000

Pkg

Weightqty(1 pce) g

20

22.50

1SNK161004S0201

Accessories

ZS16 screw clamp terminal blocks
Feed-through - 10 mm 0.394 in spacing
16 mm²
4 AWG

Description–– Save space by connecting conductors up to 16 mm² (without insulated ferrule, CB certified) 4 AWG in just
10 mm 0.394 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
1SNK161006F0014

Description

Color

Feed-through

Grey
Blue
Orange29.8 1.17"

10 mm 0.394 in spacing

50.3 1.98"

57.8 2.28"

56.1 2.21"

Pkg

Part Number

ZS16
ZS16-BL
ZS16-OR1SNK510010R0000
1SNK510020R0000
1SNK510030R0000

Main technical data

Weightqty(1 pce) g

25
25
25

20.20
20.20
20.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 10 mm²
A6-B6
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
76 A / 16 mm²
1920 A

24 ... 4 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 76 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 67 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS16

Type

24 ... 4 AWG
24 ... 8 AWG
20 ... 10 AWG

Flat screwdriverToolØ 5.5 mm
Ø 0.217 in

20 ... 10 AWG
67 A / 4 AWG

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque100 kA
600 V

1000 V
8000 VIP20

TH 35-7.5,
TH 35-15
13.5 mm0.531 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
Description

2
1
2
3

3

4

5

6

4
5
6

7

8

7
8

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
76 A (IEC)3 poles
76 A (IEC)4 poles
76 A (IEC)
5 poles
76 A (IEC)
10 poles76 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 inProtecting covers 10 mm 0.394 in spacing
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB10-2
1SNK910302R0000
JB10-3
1SNK910303R0000
JB10-4
1SNK910304R0000
JB10-5
1SNK910305R0000
JB10-10
1SNK910310R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
PL10
1SNK900621R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
40
30
20
10
20
20
20
20
10
1680
22
20
10

14.00
2.20
4.60
7.10
9.40
12.00
24.00
2.80
0.20
5.20
1.70
2.40
3.10
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS16

Green-yellow

Type
ZS16-PEPart Number
1SNK510150R0000

Pkg

Weightqty(1 pce) g

20

32.00

Technical data valid for copper conductors only.

PAGE 233

1SNK161017S0201

1

ZS25 screw clamp terminal blocks
Feed-through - 12 mm 0.472 in spacing
25 mm²
3 AWG

Description–– Save space by connecting conductors up to 25 mm² (without insulated ferrule, CB certified) 3 AWG in just
12 mm 0.472 in spacing,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

Ordering details
1SNK161081V0014

Description

Color

Feed-through

Grey
Blue
Yellow

57.8 2.28"
29.8 1.17"

12 mm 0.472 in spacing

50.3 1.98"

56.1 2.21"

Part Number

ZS25
ZS25-BL
ZS25-YL

1SNK512010R0000
1SNK512020R0000
1SNK512060R0000

Main technical data

Pkg

Weightqty(1 pce) g

25
25
25

21.40
21.40
21.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 25 mm²
0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
A6-B6
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
76 A / 16 mm²
101 A / 25 mm²
1920 A

24 ... 3 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 69 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 100 A

1 conductor
per clamp

ZS25

Type

24 ... 4 AWG
24 ... 8 AWG
20 ... 10 AWG

1000 V
8000 V
IP20

Flat screwdriverToolØ 5.5 mm
Ø 0.217 in

20 ... 10 AWG
100 A / 3 AWG

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque100 kA
600 V

TH 35-7.5,
TH 35-15
13.5 mm0.531 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2
3

3

4
4
5

5

7

6

8

6
7
8

10 mm
0.394 in
2.2 mm0.087 in
2 poles
76 A (IEC)3 poles
76 A (IEC)
5 poles
76 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Circuit separators 0 mm
0 in
3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 inProtecting covers 10 mm 0.394 in spacing
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Dark grey
Dark grey
OrangeOrangeDark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
JB12-2
1SNK912302R0000
JB12-3
1SNK912303R0000
JB12-5
1SNK912305R0000
JB85-3
1SNK900603R0000
CS
1SNK900101R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
PL10
1SNK900621R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
20
10
20
20
20
20
10
1680
22
20
10

14.00
2.20
4.90
7.60
12.90
2.80
0.20
5.20
1.70
2.40
3.10
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS25

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZS25-PEPart Number
1SNK512150R0000

Pkg

Weightqty(1 pce) g

20

38.00

1SNK161078S0201

8

Color

ZS35 screw clamp terminal blocks
Feed-through - 16 mm 0.630 in spacing
Description

35 mm²

Closed terminal block:–– No end section needed,–– Optimized rigidity,–– Perfectly adapted to solar applications: voltage is rated 1000 V AC / DC IEC.

0 AWG

1SNK161004F0014

Ordering details
Description
Feed-through

Color
Closed block

Type

Grey
Blue
Orange

ZS35
ZS35-BL
ZS35-OR1SNK516010R0000
1SNK516020R0000
1SNK516030R0000

Main technical data
ZS35

16 mm 0.630 in spacing

55.8 2.19"

63.3 2.49"
34 1.34"

Weightqty(1 pce) g

20
20
20

53.40
53.40
53.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

6 ... 35 mm²
6 ... 35 mm²
4 ... 35 mm²
4 … 35 mm²
A9-B9
6 ... 16 mm²
6 ... 16 mm²
4 … 10 mm²
125 A / 35 mm²4200 A

10 ... 0 AWG

Wire stripping
lengthIncreased safety Ex e

693 V 125 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 150 A UL 60079-7 - Class I, Zone 1, AEx e II

1 conductor
per clamp
59 2.32"

Pkg

Part Number

10 ... 2 AWG
10 ... 2 AWG
10 ... 6 AWG

Flat screwdriverToolØ 6.5 mm
Ø 0.256 in

12 ... 8 AWG
150 A / 0 AWG

2.9 Nm ± 0.1
25.7 lb.in ± 0.885

Torque100 kA
600 V

1000 V
8000 VIP10

TH 35-7.5,
TH 35-15
17 mm
0.669 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
Description

2
1
2

3

5

4
3
4
5

Color

10 mm
0.394 in
2 poles
125 A (IEC)3 poles
125 A (IEC)4 poles
125 A (IEC)
5 poles
125 A (IEC)
10 poles
125 A (IEC)
Circuit separators 3 mm
0.118 inProtecting covers 16 mm 0.630 in spacing
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Dark grey
OrangeDark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB16-2
1SNK916302R0000
JB16-3
1SNK916303R0000
JB16-4
1SNK916304R0000
JB16-5
1SNK916305R0000
JB16-10
1SNK916310R0000
CS-R1
1SNK900103R0000
PL16
1SNK900622R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
10
10
10
10
10
20
10
1680
22
20
10

24.00
10.00
16.00
22.00
28.00
56.60
5.20
4.60
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS35

Green-yellow

Type
ZS35-PEPart Number
1SNK516150R0000

Pkg

Weightqty(1 pce) g

20

81.80

Technical data valid for copper conductors only.

PAGE 235

1SNK161019S0201

1

ZS50 screw clamp terminal blocks
Feed-through - 16 mm 0.630 in spacing
50 mm²0 AWG

Description
Combine high performance with compact dimensions:–– Connect conductors up to 50 mm² (CB certified) 0 AWG in just 16 mm 0.630 in spacing,–– Perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC and 1000 V UL,–– Closed terminal block: no end section needed, optmized rigidity.

1SNK161084V0014

Ordering details
Description
Feed-through

Color

Type

Closed block

Grey
Blue
YellowRed
Black

Part Number

ZS50
ZS50-BL
ZS50-YL
ZS50-RD
ZS50-BK

1SNK516011R0000
1SNK516021R0000
1SNK516060R0000
1SNK516063R0000
1SNK516064R0000

Main technical data
ZS50

16 mm 0.630 in spacing

61.8 2.43"

69.3 2.73"
31.9 1.25"

Weight(1 pce) g

20
20
20
20
20

52.90
52.90
52.90
52.90
52.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
Dia.11
1 … 25 mm²
1 … 25 mm²
1 … 16 mm²
150 A / 50 mm²6000 A

18 … 0 AWG

Wire stripping
lengthIncreased safety Ex e

880 V 150 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC

1 conductor
per clamp

63.6 2.50"

Pkg
qty

18 … 0 AWG
18 … 0 AWG
18 … 4 AWG

1000 V
8000 V
IP10

Flat screwdriverToolØ 6.5 mm
Ø 0.256 in

18 … 4 AWG
140 A / 0 AWG

3 Nm ± 0.50
26.6 lb.in ± 4.43

Torque100 kA
1000 VTH 35-7.5,
TH 35-15
17 mm
0.669 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

Description

2
1
2

End stops
Jumper bars

3

Terminal block
markers

3

8

Color
10 mm
0.394 in
2 poles
125 A (IEC)3 poles
125 A (IEC)4 poles
125 A (IEC)
5 poles
125 A (IEC)
10 poles
125 A (IEC)
Blank marker
Blank card

Dark grey
OrangeWhite

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB16-2
1SNK916302R0000
JB16-3
1SNK916303R0000
JB16-4
1SNK916304R0000
JB16-5
1SNK916305R0000
JB16-10
1SNK916310R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
10
10
10
10
10
1680
22
20
10

24.00
10.00
16.00
22.00
28.00
56.60
0.27
10.00
14.00
0.20

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS50

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZS50-PEPart Number
1SNK516151R0000

Pkg

Weightqty(1 pce) g

20

83.00

1SNK161069S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS70 screw clamp terminal blocks
Feed-through - 22 mm 0.866 in spacing
70 mm²00 AWG

Description
Closed terminal block:–– No end section needed,–– Optimized rigidity,–– Perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC and 1000 V UL.

1SNK161044F0014

Ordering details
Description
Feed-through

Color

Type

Closed block

Grey
Blue
Yellow

ZS70
ZS70-BL
ZS70-YL

1SNK522010R0000
1SNK522020R0000
1SNK522060R0000

Main technical data
ZS70

75 2.95"

82.5 3.25"
39.5 1.56"

22 mm 0.866 in spacing

Weightqty(1 pce) g

10
10
10

158.10158.10158.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

16 ... 95 mm²
16 ... 70 mm²
16 ... 50 mm²
16 ... 50 mm²
B11
16 ... 35 mm²
16 ... 35 mm²
16 mm²
192 A / 70 mm²8400 A

4 ... 00 AWG

Wire stripping
length4 ... 2 AWG

Tool

Increased safety Ex e

693 V 192 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 159 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp
78.4 3.09"

Pkg

Part Number

Allen keyØ 6 mmØ 0.236 in

6 AWG
159 A / 00 AWG

6.5 Nm ± 0.5
57.5 lb.in ± 4.43

Torque100 kA
1000 V

1000 V
8000 VIP10

TH 35-7.5,
TH 35-15
25 mm
0.984 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
Description

2
1
2

End stops
Jumper bars

3

Terminal block
markers

3

Color
10 mm
0.394 in
2 poles
192 A (IEC)3 poles
192 A (IEC)
5 poles
192 A (IEC)
10 poles
192 A (IEC)
Blank marker
Blank card

Dark grey

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB22-2
1SNK922302R0000
JB22-3
1SNK922303R0000
JB22-5
1SNK922305R0000
JB22-10
1SNK922310R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
5
5
5
5
1680
22
20
10

24.00
27.00
43.30
76.10
157.40
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS70

Green-yellow

Type
ZS70-PEPart Number
1SNK522150R0000

Pkg

Weightqty(1 pce) g

10222.00Technical data valid for copper conductors only.

PAGE 237

1SNK161021S0201

1

ZS95 screw clamp terminal blocks
Feed-through - 26 mm 1.024 in spacing
95 mm²0000 AWG

Description
Closed terminal block:–– No end section needed,–– Optimized rigidity,–– Perfectly adapted to solar applications: 1250 V DC (1000 V AC) IEC and 1000 V UL.

1SNK161025F0014

Ordering details
Description
Feed-through

Color

Type

Closed block

Grey
Blue
Yellow

ZS95
ZS95-BL
ZS95-YL

1SNK526010R0000
1SNK526020R0000
1SNK526060R0000

Main technical data
ZS95

79.5 3.13"

87 3.43"
46 1.81"

26 mm 1.024 in spacing

Weightqty(1 pce) g

10
10
10

215.10215.10215.10

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

35 ... 120 mm²
35 ... 95 mm²
35 ... 50 mm²
35 ... 50 mm²
B12
25 ... 35 mm²
25 ... 35 mm²
16 mm²232 A / 95 mm²11400 A

2 ... 0000 AWG

Wire stripping
length4 ... 2 AWG

Tool

Increased safety Ex e

693 V 232 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 600 V 230 A UL 60079-7 - Class I, Zone 1, AEx e II

1 conductor
per clamp
87 3.43"

Pkg

Part Number

Allen keyØ 6 mmØ 0.236 in

6 AWG
230 A / 0000 AWG

9.25 Nm ± 0.25
81.7 lb.in ± 2.21

Torque100 kA
1000 V

1000 V
8000 VIP10

TH 35-7.5,
TH 35-15
26 mm
1.024 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

Description

2
1
2

End stops
Jumper bars

3

Terminal block
markers

3

Color
10 mm
0.394 in
2 poles
232 A (IEC)3 poles
232 A (IEC)
5 poles
232 A (IEC)
10 poles
232 A (IEC)
Blank marker
Blank card

Dark grey

White

Universal wire markers holder

8

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB26-2
1SNK926302R0000
JB26-3
1SNK926303R0000
JB26-5
1SNK926305R0000
JB26-10
1SNK926310R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
5
5
5
5
1680
22
20
10

24.00
41.20
65.70
115.70241.50
0.27
10.00
14.00
0.20

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with ZS95

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreen-yellow

Type
ZS95-PEPart Number
1SNK526150R0000

Pkg

Weightqty(1 pce) g

10278.00

1SNK161023S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS150 screw clamp terminal blocks
Feed-through - 31 mm 1.220 in spacing
150 mm²
350 Kcmil

Description–– Perfectly adapted to solar applications : 1500V DC (1000V AC) IEC and 1000V UL,–– Closed terminal block: no end section needed, optimized rigidity,–– Ease your voltage monitoring or distribution with the 2 built-in derivations,–– Use of jumper bars requires the user to cut-out the partition.

1SNK161150V0014

Ordering details
Description

Color

Type

Part Number

Closed block with 2 x 10 mm²
derivations.

Feed-through

Grey
Blue
Yellow

ZS150
ZS150-BL
ZS150-YL

1SNK531010R0000
1SNK531020R0000
1SNK531060R0000

Main technical data
ZS150

Mounting instructions

114.5 4.50"

110 4.33"

36.5 1.43"

31 mm 1.220 in spacing

UL

Rail

Connecting capacity

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rigid: Solid/Stranded
Derivation with
1 conductor per Flexible without ferrule
clamp
Gauge
Rated current / Rated cross section
Main circuit Copper
Aluminium
Derivation
Rated short-time withstand current (1s)
V AC
Rated voltage
V DC
Impulse withstand voltage
Protection

35 ... 185 mm² 2 … 350 Kcmil 2 … 350 Kcmil Main circuit
50 ... 150 mm²
Wire stripping
lengthB14
Tool
0.5 ... 16 mm² 20 ... 8 AWG 20 ... 8 AWG
0.5 ... 10 mm² 20 ... 8 Kcmil 20 ... 8 Kcmil
B6
TorqueIncreased safety Ex e1000 V 309 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC

Main circuit with
1 conductor per
clamp
119.4 4.70"

Pkg Weight(1 pce) g
5318.005318.005318.00qty

CSA

309 A / 150 mm² 310 A / 350 Kcmil 310 A / 350 Kcmil Derivation
Wire stripping
57 A / 10 mm² 50 A / 8 AWG 50 A / 8 AWG
length18000 A
Tool
1000 V
1000 V
1000 V
1500
12000 VTorqueIP10NEMA 1

TH 35-7.5,
TH 35-15
40 mm
1.575 inAllen keyØ 8 mmØ 0.315 in
20 Nm
177 lb.in
12 mm
0.47 inFlat screwdriverØ 4 mmØ 0.157 in
1.2 Nm ... 1.4 Nm
10.6 lb.in ... 12.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

Accessories

3

Description

2

4

Color

1
2

End stops
Jumper bars

10 mm
2 poles
3 poles

3
4

Protecting covers
Terminal block
Blank card
markers
Blank marker
Blank card

0.394 in
309 A (IEC)309 A (IEC)

Universal wire markers holder

Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
BJMI31.2
1SNA206053R0700
BJMI31.3
1SNA206054R0000
CPBP1
1SNA399788R1600
RC1010
1SNA238000R1600
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1
1
20
10
1680
22
20
10

24.00
120.00190.00
0.40
1.30
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161093S0201

1

Technical data valid for copper conductors only.

PAGE 239

ZS240 screw clamp terminal blocks
Feed-through - 36 mm 1.417 in spacing
240 mm²
500 Kcmil

Description–– Perfectly adapted to solar applications : 1500V DC (1000V AC) IEC and 1000V UL,–– UL Certified for aluminum cables use - Closed terminal block: no end section needed, optimized rigidity,–– Ease your voltage monitoring or distribution with the 2 built-in derivations,–– Use of jumper bars requires the user to cut-out the partition.

1SNK161153V0014

Ordering details
Description

Color

Type

Part Number

Closed block with 2 x 10 mm²
derivations.

Feed-through

Grey
Blue
Yellow

ZS240
ZS240-BL
ZS240-YL

1SNK536010R0000
1SNK536020R0000
1SNK536060R0000

Main technical data
ZS240

Mounting instructions

124.5 4.90"

110 4.33"

36.5 1.43"

36 mm 1.417 in spacing

UL

Rail

Connecting capacity

IEC

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with insulated ferrule
Gauge
Rigid: Solid/Stranded
Derivation with
1 conductor per Flexible without ferrule
clamp
Gauge
Rated current / Rated cross section
Main circuit Copper
Aluminium
Derivation
Rated short-time withstand current (1s)
V AC
Rated voltage
V DC
Impulse withstand voltage
Protection

50 ... 300 mm² 0 … 500 Kcmil 0 … 500 Kcmil Main circuit
50 ... 240 mm²
Wire stripping
lengthB14
Tool
0.5 ... 16 mm² 20 ... 8 AWG 20 ... 8 AWG
0.5 ... 10 mm² 20 ... 8 Kcmil 20 ... 8 Kcmil
B6
TorqueIncreased safety Ex e1000 V 415 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC

Main circuit with
1 conductor per
clamp
119.4 4.70"

Pkg Weight(1 pce) g
5366.005366.005366.00qty

CSA

415 A / 240 mm² 380 A / 500 Kcmil 380 A / 500 Kcmil Derivation
271 / 500 Kcmil 271 / 500 Kcmil
Wire stripping
57 A / 10 mm² 50 A / 8 AWG 50 A / 8 AWG
length28800 A
Tool
1000 V
1000 V
1000 V
1500
12000 VTorqueIP10NEMA 1

TH 35-7.5,
TH 35-15
38 mm
1.496 inAllen keyØ 8 mmØ 0.315 in
25 Nm
221.3 lb.in
12 mm
0.47 inFlat screwdriverØ 4 mmØ 0.157 in
1.2 Nm ... 1.4 Nm
10.6 lb.in ... 12.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

ATEX

IECEx

BV

Accessories
1

3

Description

2

4

Color

1
2

End stops
Jumper bars

10 mm
2 poles
3 poles

3
4

Protecting covers
Terminal block
Blank card
markers
Blank marker
Blank card

0.394 in
415 A (IEC)415 A (IEC)

Universal wire markers holder

8

Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
BJMI36.2
1SNA206126R2500
BJMI36.3
1SNA206223R0600
CPBP2
1SNA399787R0500
RC1010
1SNA238000R1600
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1
1
20
10
1680
22
20
10

24.00
170.00260.00
1.30
1.30
0.27
10.00
14.00
0.20

1SNK161094S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-PE screw clamp terminal blocks
Ground - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.

1SNK161018F0014

Ordering details
Description

Color
Screwless rail connection

Ground1 conductor
per clamp

Pkg

Part Number

Green-yellow

ZS4-PE

1SNK505150R0000

IEC

UL - CSARail

Main technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

0.2 ... 4 mm²
24 ... 12 AWG
0.22 ... 4 mm²0.22 ... 4 mm²
24 ... 12 AWG
0.22 ... 2.5 mm² 24 ... 14 AWG
A3-B3

56.3 2.22"

48.8 1.92"(1 pce) g

20

12.10

TH 35-7.5,
TH 35-15
10.5 mm0.412 in

Wire stripping
lengthFlat screwdriverTool

59.5 2.26"

26.7 1.05"

Weightqty

Mounting instructions

Connecting capacity

ZS4-PETypeØ 3.5 mm
Ø 0.138 in

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

12 AWG
396 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1960
22
20
10

14.00
2.20
5.20
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161002S0201

1

Technical data valid for copper conductors only.

PAGE 241

ZS6-PE screw clamp terminal blocks
Ground - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.

1SNK161017F0014

Ordering details
Description

Color
Screwless rail connection

Ground1 conductor
per clamp

Pkg

Part Number

Green-yellow

ZS6-PE

1SNK506150R0000

IEC

UL - CSA

Rail

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

56.3 2.22"

48.8 1.92"(1 pce) g

20

13.70

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverTool

59.5 2.26"

26.7 1.05"

Weightqty

Mounting instructions

Connecting capacity

ZS6-PETypeØ 4 mmØ 0.157 in

Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

10 AWG
636 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161015S0201

8

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS6-3S-PE screw clamp terminal blocks
Ground with 3 connections - 6 mm 0.236 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– rail contact non operator dependent, secured snap on or off the rail,–– Same profile as ZS6-3S for aligned marking and identical end section.

10 AWG

1SNK161090V0014

Ordering details
Description

Color
Screwless rail connection

GroundPart Number

Green-yellow

ZS6-3S-PE

1SNK506151R0000

IEC

UL - CSA

Rail

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

57.2 2.25"

49.7 1.96"

Weight(1 pce) g

25

16.20

Rated cross section
Maximum cross section
Rated short-time withstand current (1s)Maximum short-time withstand current (1s)

4 mm²
6 mm²
480 A
480 A

10 AWG

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

Ø 4 mmØ 0.157 in

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque636 A

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriver

Tool

68.5 2.69"

35.65 1.40"

Pkg
qty

Mounting instructions

Connecting capacity

ZS6-3S-PE

Type

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-3S
1SNK505912R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.50
5.20
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161080S0201

1

Technical data valid for copper conductors only.

PAGE 243

ZS6-4S-PE screw clamp terminal blocks
Ground with 4 connections - 6 mm 0.236 in spacing
Description

6 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– rail contact non operator dependent, secured snap on or off the rail,–– Same profile as ZS6-4S for aligned marking and identical end section.

10 AWG

1SNK161091V0014

Ordering details
Description

Color
Screwless rail connection

GroundPart Number

Green-yellow

ZS6-4S-PE

IEC

UL - CSA

Rail

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

79.2 3.12"

1SNK506152R0000

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

49.7 1.96"

57.2 2.3"

6 mm 0.236 in spacing

Weight(1 pce) g

25

19.40

Rated cross section
Maximum cross section
Rated short-time withstand current (1s)Maximum short-time withstand current (1s)

4 mm²
6 mm²
480 A
480 A

10 AWG

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

Ø 4 mmØ 0.157 in

0.75 Nm ± 0.05
6.64 lb.in ± 0.443

Torque636 A

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriver

Tool

35.7 1.4"

Pkg
qty

Mounting instructions

Connecting capacity
ZS6-4S-PE

Type

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
3.10
5.20
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161081S0201

8

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS10-PE screw clamp terminal blocks
Ground - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.

1SNK161016F0014

Ordering details
Description

Color
Screwless rail connection

Ground1 conductor
per clamp

Pkg

Part Number

Green-yellow

ZS10-PE

1SNK508150R0000

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²
A5-B5

24 ... 6 AWG

Wire stripping
lengthMain technical data
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 8 AWG
24 ... 8 AWG

56.3 2.22"(1 pce) g

20

22.50

TH 35-7.5,
TH 35-15
12 mm
0.472 inFlat screwdriverTool

59.5 2.26"

26.7 1.05"

Weightqty

Mounting instructions

Connecting capacity

ZS10-PEType

Ø 4 mmØ 0.157 in

Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161016S0201

1

Technical data valid for copper conductors only.

PAGE 245

ZS16-PE screw clamp terminal blocks
Ground - 10 mm 0.394 in spacing
16 mm²

1SNK161019F0014

4 AWG

Description
Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– Rail contact non operator dependent,–– Performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail,–– PE.N function available by combining ZS16-PE with ZS16-BL and 2 poles jumper bar JB10-2.

Ordering details
Description

Color
Screwless rail connection

GroundType

Green-yellow

ZS16-PE

1SNK510150R0000

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 10 mm²
A6-B6

24 ... 4 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

60.6 2.39"

56.3 2.22"

10 mm 0.394 in spacing(1 pce) g

20

32.00

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 4 AWG
24 ... 8 AWG

TH 35-7.5,
TH 35-15
13.5 mm0.531 inFlat screwdriverTool

27.9 1.10"

Weightqty

Mounting instructions

Connecting capacity
ZS16-PE

Pkg

Part Number

Ø 5.5 mm
Ø 0.217 in

Rated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG
2544 A

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161018S0201

8

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS25-PE screw clamp terminal blocks
Ground - 12 mm 0.472 in spacing
Description

25 mm²

Improve the safety of your installation in the event of a short-circuit thanks to our screwless rail contact:–– rail contact non operator dependent, secured snap on or off the rail,–– Same profile as ZS25 for aligned marking and identical end section.

3 AWG

Ordering details
1SNK161092V0014

Description

Color
Screwless rail connection

GroundTypePart Number

Green-yellow

ZS25-PE

1SNK512150R0000

IEC

UL - CSA

Rail

0.5 ... 25 mm²
0.5 ... 25 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
A6-B6

24 ... 3 AWG

Wire stripping
lengthMain technical data

ZS25-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 4 AWG
24 ... 8 AWG

57.8 2.28"

50.3 1.98"

20

38.00

Ø 5.5 mm
Ø 0.217 in

Rated cross section
Maximum cross section
Rated short-time withstand current (1s)Maximum short-time withstand current (1s)

16 mm²25 mm²1920 A
3000 A

3 AWG

Protection

IP20

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

1.8 Nm ± 0.2
15.9 lb.in ± 1.77

Torque3204 ATH 35-7.5,
TH 35-15
13.5 mm0.531 inFlat screwdriverTool
63.6 2.5"

29.8 1.17"

Weight(1 pce) g

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

12 mm 0.472 in spacing

CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161082S0201

1

Technical data valid for copper conductors only.

PAGE 247

ZS35-PE screw clamp terminal blocks
Ground - 16 mm 0.630 in spacing
35 mm²
2 AWG

Description
Reliable electrical and mechanical contact with the rail that exceeds the requirements of IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

Ground1SNK161005F0014

Color

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

ZS35-PEIEC

UL - CSA

Rail

6 ... 35 mm²
6 ... 35 mm²
4 ... 35 mm²
4 … 35 mm²A910 ... 2 AWG

Wire stripping
length35 mm²4200 A

Rated cross section
Rated short-time withstand current (1s)63.3 2.49"

Green-yellow

1SNK516150R0000

Weightqty(1 pce) g

20

81.80

Mounting instructions

Connecting capacity

ZS35-PE

Pkg

Part Number

Main technical data
1 conductor
per clamp

59 2.32"Type

10 ... 2 AWG
10 ... 2 AWG

TH 35-7.5,
TH 35-15
17 mm
0.669 inFlat screwdriver

Tool
Screw clamp

Ø 6.5 mm
Ø 0.256 in
Ø 5.5
Ø 0.217

Rail connection
screw

2 AWG
4032 ATorqueScrew clamp

2.65 Nm ± 0.15
23.4 lb.in ± 1.33
1.6 Nm ± 0.15 Nm
14.2 lb.in ± 1.33 lb.in

Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

34 1.34"

16 mm 0.630 in spacing

Accessories
1

Description

2
1
2
3

3

End stops
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
1680
22
20
10

24.00
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161020S0201

8

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS35-PEN screw clamp terminal blocks
Ground + neutral - 32 mm 1.260 in spacing
Description

35 mm²

N

Simplify your PE.N connection with ZS35-PE block connected to ZS35-BL through a pre-mounted jumper.

Ordering details
Description

Color

1SNK161063F0014

Ground + neutral

ZS35-PENIEC

UL - CSA

1 conductor
per clamp

Part Number
1SNK516170R0000

Pkg

Weightqty(1 pce) g

10

236.00

Mounting instructions

Connecting capacity
Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

6 ... 35 mm²
6 ... 35 mm²
6 ... 35 mm²
6 ... 35 mm²A910 ... 2 AWG

Wire stripping
lengthRail connection
screw
TorqueScrew clamp

IP10

Protection

Rail

Tool
Screw clamp

35 mm²4200 A

Rated cross section
Rated short-time withstand current (1s)63.3 2.49"

Green-yellow

Main technical data

ZS35-PEN

60.3 2.37"

Type

NEMA 1

Rail connectionscrew

TH 35-7.5,
TH 35-15
17 mm
0.669 inFlat screwdriverØ 6.5 mm
Ø 0.256 in
Ø 5.5
Ø 0.2172.65 Nm ± 0.15
23.5 lb.in ± 1.33
1.6 Nm ± 0.15 Nm
14.2 lb.in ± 1.33 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

EAC

34 1.34"

32 mm 1.260 in spacing

Accessories
Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161047S0201

1

Technical data valid for copper conductors only.

PAGE 249

ZS50-PE screw clamp terminal blocks
Ground - 16 mm 0.630 in spacing
50 mm²0 AWG

Description–– Reliable electrical and mechanical contact with the rail that exceeds the requirements of the IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

Ground1SNK161093V0014

Color
Green-yellow

ZS50-PE

1SNK516151R0000

IEC

UL - CSARail

1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
1 … 50 mm²
Dia.11

18 … 0 AWG

Wire stripping
lengthPkg

Weightqty(1 pce) g

20

83.00

Mounting instructions

Connecting capacity

ZS50-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

50 mm²6000 A

Rated cross section
Rated short-time withstand current (1s)69.3 2.73"

Part Number

Main technical data
1 conductor
per clamp

63.6 2.50"

Type

18 … 0 AWG
18 … 0 AWG

Tool
Screw clamp
Rail connection
screw

0 AWG
6420 ATorqueScrew clamp
Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II

TH 35-7.5,
TH 35-15
17 mm
0.669 inFlat screwdriverØ 6.5 mm
Ø 0.256 in
Ø 6.5
Ø 0.256

3 Nm ± 0.50
26.6 lb.in ± 4.43
3 Nm ± 0.25 Nm
26.553 lb.in ± 2.21 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

31.9 1.25"

CB

RoHS

USR

CSA

EAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

16 mm 0.630 in spacing

Accessories
1

Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161070S0201

8

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS70-PE screw clamp terminal blocks
Ground - 22 mm 0.866 in spacing
70 mm²00 AWG

Description
Reliable electrical and mechanical contact with the rail that exceeds the requirements of IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

Ground1SNK161045F0014

Color

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge(1 pce) g

10222.00

Green-yellow

ZS70-PEIEC

UL - CSARail

TH 35-15

16 ... 95 mm²
16 ... 70 mm²
16 ... 50 mm²
16 ... 50 mm²
B11

4 ... 00 AWG

Wire stripping
length25 mm
0.984 in

70 mm²8400 A

Rated cross section
Rated short-time withstand current (1s)82.6 3.25"

1SNK522150R0000

Weightqty

Mounting instructions

Connecting capacity

ZS70-PE

Pkg

Part Number

Main technical data
1 conductor
per clamp

74 2.91"

Type

Allen key

Tool
Screw clamp

Ø 6 mmØ 0.236 in
Ø 4
Ø 0.158

Rail connectionscrew

00 AWG
8088 ATorqueScrew clamp

6.5 Nm ± 0.5
57.5 lb.in ± 4.43
1.9 Nm ± 0.1 Nm
16.82 lb.in ± 0.885 lb.in

Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

39.5 1.56"

22 mm 0.866 in spacing

Accessories
Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161022S0201

1

Technical data valid for copper conductors only.

PAGE 251

ZS95-PE screw clamp terminal blocks
Ground - 26 mm 1.024 in spacing
95 mm²0000 AWG

Description
Reliable electrical and mechanical contact with the rail that exceeds the requirements of IEC 60947-7-2
terminal block standard.

Ordering details
Description
Screw rail connection

Ground1SNK161024F0014

Color

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge(1 pce) g

10278.00

Green-yellow

ZS95-PEIEC

UL - CSARail

TH 35-15

35 ... 120 mm²
35 ... 95 mm²
35 ... 50 mm²
35 ... 50 mm²B12

2 ... 0000 AWG

Wire stripping
length26 mm
1.024 in

95 mm²11400 A

Rated cross section
Rated short-time withstand current (1s)

87 3.43"

1SNK526150R0000

Weightqty

Mounting instructions

Connecting capacity

ZS95-PE

Pkg

Part Number

Main technical data
1 conductor
per clamp

87 3.43"

Type

Allen key

Tool
Screw clamp

0000 AWG
12840 A

Ø 6 mmØ 0.236 in
Ø 4
Ø 0.158

Rail connection
screw
TorqueScrew clamp

9.25 Nm ± 0.25
81.7 lb.in ± 2.2
1.9 Nm ± 0.1 Nm
16.82 lb.in ± 0.885 lb.in

Rail connection
screw

Protection

IP10

NEMA 1

Explosive atmosphere classification

IM2 II 2 GD Ex eb I/II/IIIC – Class I, Zone 1, AEx e II, Ex e II U

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

46 1.81"

26 mm 1.024 in spacing

Accessories
1

Description

2
1
2

End stops
Terminal block
markers

Color
10 mm
0.394 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
1680
22
20
10

24.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161024S0201

8

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-S screw clamp terminal blocks
Disconnect with blade - 5.2 mm 0.205 in spacing
4 mm²
10 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

Ordering details

1SNK161002F0014

Description

Color
Profile aligned with ZS4Disconnect

Grey
Blue
Orange26.7 1.05"

5.2 mm 0.205 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"

53 2.09"

Pkg

Part Number

ZS4-S
ZS4-S-BLZS4-S-OR

1SNK505310R0000
1SNK505320R0000
1SNK505330R0000

Main technical data

Weightqty(1 pce) g

50
50
50

8.60
8.60
8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²
0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
25 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp
ZS4-S

Type

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
25 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

Description

2
1
2
3

3

5

4

6

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
Circuit separators 3 mm
0.118 inShield connectors
Protecting covers 5.2 mm 0.205 in spacing
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey
Dark grey
Transparent
White

Grey

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
CS-R1
1SNK900103R0000
SHBS
1SNK900600R0000
PL5
1SNK900618R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
10
1960
22
20
10

14.00
2.20
1.80
6.00
5.20
3.50
1.50
0.23
9.00
10.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161010S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

PAGE 253

ZS4-S-T screw clamp terminal blocks
Disconnect with blade - with test socket - 5.2 mm 0.205 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets,–– Screwdriver or hand operated disconnect blade,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

10 AWG

Ordering details
1SNK161034F0014

Description
Disconnect

Color
Profile aligned with ZS4, with 2 test
sockets DIA 2 mm 0.079 in

Type

Grey
Blue
OrangeGrey

Profile aligned with ZS4, with 2 test
sockets DIA 2.3 mm 0.091 in

ZS4-S-T2ZS4-S-T2-BL
ZS4-S-T2-OR
ZS4-S-T2.3

Main technical data

Part Number
1SNK505311R0000
1SNK505321R0000
1SNK505331R0000
1SNK505312R0000

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
25 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"
26.7 1.05"

5.2 mm 0.205 in spacing

Weight(1 pce) g

50
50
50
50

8.90
8.90
8.90
8.80

Mounting instructions

Connecting capacity
ZS4-S-T

53 2.09"Pkg
qty

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
25 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

3

4

8

5

Description

2

6

1
2
3
4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
Circuit separators 3 mm
0.118 inShield connectors
Protecting covers 5.2 mm 0.205 in spacing
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey
Dark grey
Transparent
White

Grey

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
CS-R1
1SNK900103R0000
SHBS
1SNK900600R0000
PL5
1SNK900618R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
10
1960
22
20
10

14.00
2.20
1.80
6.00
5.20
3.50
1.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161042S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-S-R1 screw clamp terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing
Description

4 mm²–– Simplify the alternated distribution thanks to the two jumper channels aligned with ZS4 feed-through terminal blocks,–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver.

10 AWG

Ordering details
1SNK161003F0014

Description

Color
Profile aligned with ZS4-SF

Disconnect

Type

Grey
Blue
OrangeZS4-S-R1
ZS4-S-R1-BL
ZS4-S-R1-OR

1SNK506310R0000
1SNK506320R0000
1SNK506330R0000

Main technical data
ZS4-S-R1

6 mm 0.236 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"
26.7 1.05"

Weightqty(1 pce) g

50
50
50

13.20
13.20
13.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
26 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

70.5 2.78"

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
26 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
Description

2

3

4

5

6

1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161012S0201

1

Technical data valid for copper conductors only.

PAGE 255

ZS4-S-T-R1 screw clamp terminal blocks
Disconnect with blade - with test socket - 6 mm 0.236 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets,–– Screwdriver or hand operated disconnect blade,–– Simplify the alternated distribution thanks to the two jumper channels aligned with ZS4 feed-through terminal blocks.

1SNK161035F0014

10 AWG

Ordering details
Description

Color
Profile aligned with ZS4-SF, with 2
test sockets DIA 2 mm 0.079 in

Disconnect

Grey
Blue
OrangeGrey

Profile aligned with ZS4-SF, with 2
test sockets DIA 2.3 mm 0.091 in

ZS4-S-T-R1

Type
ZS4-S-T2-R1
ZS4-S-T2-R1-BL
ZS4-S-T2-R1-OR
ZS4-S-T2.3-R1

Main technical data
70.5 2.78"

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"
26.7 1.05"

1SNK506311R0000
1SNK506321R0000
1SNK506331R0000
1SNK506312R0000

Weightqty(1 pce) g

50
50
50
50

14.20
14.20
14.20
14.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
26 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

6 mm 0.236 in spacing

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
26 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque
150 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
Description
1

3

5

Type

Part Number

1
2

End stops
Jumper bars

3
4
5

Test connectors
Spacers
Terminal block
markers4

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card

Dark grey

Universal wire markers holder

Grey

OrangeDark grey
Dark grey
White

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161045S0201

8

Color

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS6-S screw clamp terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver,–– Same profile as ZS6 feed-through terminal block for aligned marking and identical end section use.

Ordering details

1SNK161056F0014

Description

Color
Profile aligned with ZS6Disconnect

Grey
Blue

26.7 1.05"

6 mm 0.236 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"

53 2.09"

Part Number

ZS6-S
ZS6-S-BL

1SNK506315R0000
1SNK506322R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

8.60
8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 6 mm²0.22 ... 6 mm²0.22 ... 6 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²0.22 ... 2.5 mm²0.22 ... 2.5 mm²
25 A / 4 mm²
30 A / 6 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

500 V
6000 VIP20

300 V

1 conductor
per clamp
ZS6-S

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
25 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

TorqueNEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories

3

5

Description

2

4

6

1
2
3
4
5
6

End stops
End sections
Circuit separators
Shield connectors
Protecting covers
Terminal block
markers

Color
10 mm
2.2 mm3 mm

0.394 in0.087 in
0.118 in

Dark grey

6 mm 0.236 in spacing
Blank marker
Blank card

Transparent

Universal wire markers holder

Dark grey
Dark grey

White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
SHBS
1SNK900600R0000
PL6
1SNK900619R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
10
1680
22
20
10

14.00
2.20
5.20
3.50
1.80
0.27
10.00
11.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161046S0201

1

Technical data valid for copper conductors only.

PAGE 257

ZS6-S-4S-T screw clamp terminal blocks
Disconnect with blade - with test socket screws - 6 mm 0.236 in spacing
Description

6 mm²–– Recommended for energy markets and highly demanding applications requiring that only one conductor beconnected per clamp,–– Ease your disconnect and test operations with the two built-in test socket screws,–– Simplify the alternated distribution thanks to the jumper channel.

1SNK161094V0014

10 AWG

Ordering details
Description

Color

Type

with 2 test sockets DIA 2 mm
0,079 in

Disconnect

Grey

ZS6-S-4S-T2

Main technical data

Part Number
1SNK506316R0000

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 6 mm²
0.22... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
27 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 V
IP20

1 conductor
per clamp

6 mm 0.236 in spacing

59.8 2.35"

52.9 2.08"

67.3 2.64"

60.4 2.38"
35.7 1.40"

Weight(1 pce) g

50

18.40

Mounting instructions

Connecting capacity
ZS6-S-4S-T

80.7 3.18"

Pkg
qty

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
28 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque300 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

8

7

8

4
5
6
7
8

Color

10 mm
0.394 in
2.2 mm0.087 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Circuit separators 3 mm
0.118 in
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
CS-R1
1SNK900103R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
50
50
50
50
20
20
20
20
10
10
1680
22
20
10

14.00
3.10
1.30
2.10
2.90
3.60
7.40
5.20
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

1SNK161071S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS10-S screw clamp terminal blocks
Disconnect with blade - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with a screwdriver,–– Same profile as ZS10 feed-through terminal block for aligned marking and identical end section use.

Ordering details

1SNK161058F0014

Description

Color
Profile aligned with ZS10

Disconnect

Grey
Blue

26.7 1.05"

8 mm 0.315 in spacing

59.7 2.35"

52.9 2.08"
67.2 2.64"

60.4 2.37"

53 2.09"

Part Number

ZS10-S
ZS10-S-BL

1SNK508315R0000
1SNK508320R0000

Main technical data

Pkg

Weightqty(1 pce) g

50
50

8.60
8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 10 mm²0.22 ... 10 mm²0.22 ... 10 mm²0.22 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
25 A / 4 mm²
42 A / 10 mm²
480 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 VIP20

300 V

1 conductor
per clamp
ZS10-SType

24 ... 12 AWG
24 ... 12 AWG
20 ... 12 AWG

TH 35-7.5,
TH 35-15
12 mm
0.472 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
25 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

TorqueNEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories

3

Description

2

4

1
2
3
4

End stops
End sections
Circuit separators
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 in
3 mm
0.118 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
CS-R1
1SNK900103R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
1680
22
20
10

14.00
2.20
5.20
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161050S0201

1

Technical data valid for copper conductors only.

PAGE 259

ZS4-SP screw clamp terminal blocks
Disconnect with plug - 5.2 mm 0.205 in spacing
4 mm²
10 AWG

Description–– Save time with our screwless component holder plug,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

Ordering details
Description
1SNK161023F0014

Disconnect

Color
Profile aligned with ZS4, plug delivered separetely

26.7 1.05"

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"

53 2.09"

Grey

ZS4-SP

Main technical data

Part Number
1SNK505313R0000

Pkg

Weightqty(1 pce) g

50

8.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp
ZS4-SPType

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
18 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing

CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2
3

3

5

6

4
5
6
7

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
Shield connectors
Component plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

7

Dark grey
Dark grey
Grey

Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
SHBS
1SNK900600R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
20
1960
22
20
10

14.00
2.20
1.80
6.00
3.50
3.50
3.50
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161033S0201

8

4

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-SP-T2 screw clamp terminal blocks
Disconnect with plug - with test socket - 5.2 mm 0.205 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets DIA 2 mm 0.079 in,–– Save time with our screwless component holder plug,–– Same profile as ZS4 feed-through terminal block for aligned marking and identical end section use.

10 AWG

Ordering details
1SNK161036F0014

Description
Disconnect

Color

Type

Profile aligned with ZS4, with 2 test
sockets DIA 2 mm 0.079 in, plugdelivered separetely

Grey

ZS4-SP-T2

1SNK505314R0000

Main technical data

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"

53 2.09"

Pkg

Weightqty(1 pce) g

50

8.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

ZS4-SP-T2

Part Number

24 ... 10 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
18 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 126.7 1.05"

5.2 mm 0.205 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2
3

3

5

4

6

4
5
6
7

Color

End stops
10 mm
0.394 inEnd sections
2.2 mm0.087 in
Lateral jumper bars 2 poles
30 A (IEC)
10 poles
30 A (IEC)
Shield connectors
Component plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Grey

Dark grey
OrangeWhite

GreyPart Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PC5-2
1SNA113542R1000
PC5-10
1SNA113544R1200
SHBS
1SNK900600R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
20
20
20
1960
22
20
10

14.00
2.20
1.80
6.00
3.50
3.50
3.50
0.23
9.00
10.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161041S0201

7

Dark grey

TypeTechnical data valid for copper conductors only.

PAGE 261

ZS4-SP-R1 screw clamp terminal blocks
Disconnect with plug - 6 mm 0.236 in spacing
Description

4 mm²–– Simplify the alternated distribution between feed-through and disconnect circuits thanks to the two aligned
jumper channels,–– Save time with our screwless component holder plug.

10 AWG

Ordering details
1SNK161022F0014

Description
Disconnect

Color
Profile aligned with ZS4-SF, plugdelivered separetely

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"

70.5 2.78"

Grey

ZS4-SP-R1

Main technical data

Part Number
1SNK506313R0000

Pkg

Weightqty(1 pce) g

50

14.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

ZS4-SP-R1

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 126.7 1.05"

6 mm 0.236 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2

3

4
3

5

7

6

8

4
5
6
7
8

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inComponent plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
20
20
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
3.50
3.50
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161039S0201

8

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-SP-T2-R1 screw clamp terminal blocks
Disconnect with plug - with test socket - 6 mm 0.236 in spacing
Description

4 mm²–– Ease your test operations with the 2 built-in test sockets DIA 2 mm 0.079 in,–– Save time with our screwless component holder plug,–– Simplify the distribution between feed-through and disconnect circuits thanks to the two aligned jumper
channels.

1SNK161037F0014

10 AWG

Ordering details
Description
Disconnect

Color

Type

Profile aligned with ZS4-SF, with 2
test sockets DIA 2 mm 0.079 in,plug delivered separetely

Grey

ZS4-SP-T2-R1

1SNK506314R0000

Main technical data

ZS4-SP-T2-R1

73.5 2.89"

48.8 1.92"
81 3.19"56.3 2.22"
26.7 1.05"

6 mm 0.236 in spacing

Pkg

Weightqty(1 pce) g

50

14.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

70.5 2.78"

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

150 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

Accessories
1

Description

2
1
2

5

7

4

6

3
4
5
6
7

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inComponent plugs Components in series with circuit
Disconnect plugs Equipped with linking bar
Terminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
20
20
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
3.50
3.50
0.27
10.00
11.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161040S0201

3

Color

Technical data valid for copper conductors only.

PAGE 263

ZS10-SP screw clamp terminal blocks
Disconnect with plug - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Save time with our screwless component holder plug,–– Same profile as ZS10 feed-through terminal block for aligned marking and identical end section use.

Ordering details
Description
1SNK161060F0014

Disconnect

Color
Profile aligned with ZS10

Grey

26.7 1.05"

48.8 1.92"

56.3 2.22"

53 2.09"

ZS10-SP

Main technical data

Part Number
1SNK508316R0000

Pkg

Weightqty(1 pce) g

50

8.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 10 mm²0.22 ... 10 mm²0.22 ... 10 mm²0.22 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
18 A / 2.5 mm²
18 A / 10 mm²
300 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 VIP20

300 V

1 conductor
per clamp

ZS10-SPType

24 ... 8 AWG
24 ... 8 AWG
20 ... 12 AWG

Tool

20 ... 12 AWG
18 A / 6 AWG
TorqueTH 35-7.5,
TH 35-15
12 mm
0.472 inFlat screwdriverØ 4 mmØ 0.157 in

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

8 mm 0.315 in spacing

CE

RoHS

USR

CSA

EAC

Accessories
1

3

5

4

1
2
3
4
5

End stops
End sections
Component plugs
Disconnect plugs
Terminal block
markers

Color
10 mm
0.394 in
2.2 mm0.087 inComponents in series with circuit
Equipped with linking bar
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
Dark grey
Orange
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4
1SNK505910R0000
PG5
1SNK900401R0000
PG5-R1
1SNK900402R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
20
20
1680
22
20
10

14.00
2.20
3.50
3.50
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161051S0201

8

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSPB-85

8

PAGE 265SNK series, terminal blocks
Fuse protection
Optimize your control circuit protection
Our SNK series fuse terminal blocks offer a full set of featuresand functions to protect your control circuits with efficiency
and reliability.
All terminal blocks complies with the latest evolution of theinternational standards IEC 60947-7-3 (“Ancillary equipment
safety requirements for fuse terminal blocks.”) which fixes
precise temperature constraint for short-circuit and overload
protection (information in the catalogue pages related to the
products).
Qualified for worldwide markets and applications
Eco-designed according to international environmental
standards in sustainable development.

CE

RoHS
EAC

Select the right fuse holder for the right application

2 Expert for convenient circuit distribution
The expert fuse holders are equipped with two central jumper
channels for convenient common distribution and are alignedwith feed-through and disconnect terminal blocks. They
facilitate alternated potential distribution and reduce wiring.
8

Additional features for easy trouble shooting and testing
Performant blown fuse indicators
Low leakage current (< 0.5 mA) allows the protection of low
current circuits such as PLC’s inputs without any risk of circuit
disturbances.
Large voltage range (24/110 V and 110/250 V AC/DC) reduces the number of variants and allows adaptation to worldwide
applications (24/110 V range covers North american market
needs).
Easy testingSome terminal blocks are equipped with Dia 2 mm built-in
test socket screws for circuit testing while respecting the IP20
touch proof protection.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1

2

5x20 and 5x25 mm fusesCompact and high density

5x20 and 6.3x32 mm fuses
Easy potential distribution

Low leakage current blown fuseindicator.
Large voltage range: (24/110 V and
110/250 V AC and DC)

Convenient testing through built in
test socket screws

1SNK161085S0201

1 standard applications
The standard fuse holders feature compact dimensions while
offering compatibility with 5 x 20 and 5 x 25 mm fuses.
double deck terminal blocks allow efficient space reduction
for panels with space constraints.

SNK series, terminal blocks
Marshalling cabinets application
The smart choice for process
automation
Large process automation applications typically require theuse of a large number of digital or analog signals and sensors.
Indeed, marshalling cabinets ensure an important cross wiring
function, since the incoming field signal and the channel
quantity of the I/O card of the controller (DCS, large PLC’s) isalways different. They facilitate the maintenance operations
and ease the system modifications.
SNK aligned terminal blocks offering:
SNK series now features a full set of aligned terminal blocks
matching the marshalling panels typical configurations. Fuse,disconnect, feed-through and ground terminal blocks withidentical profile are providing compact and convenient solution. With only 6 mm spacing, two aligned screwless jumper
channels, central large marking as well as aligned conductor
entries, they are perfectly adapted to alternative potential
distribution while still easy to connect.

Typical marshalling configurations
Digital signals

AnalogPopular potential distribution via double centerchannel.

Disconnect functions equipped with test
points allow total isolation of circuits, easecircuit testing during start-up, test and maintenance operations.

+

-

+

-

+

-

Potential distribution for analog signals.
Ground terminal blocks allow reliable connection of cable shields to the ground sparing theuse of external shield bar.

5
8

1

3

4

1

ZS4-R2

Load

Load

Load

2

ZS4-SF

3

Load

Load

ZS4-S-R1 or ZS4-S-R2

Load

4

Load

ZS4-PE-R2

Load

5

JB6-...

PAGE 267

1SNK161086S0201

2
Load

ZS4-SF1 screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - 8 mm 0.315 in spacing
Description

4 mm²

Protect your circuit with 5x25 and 5x20 fuse terminal blocks, compliant with IEC 60947-7-3 standard (fusenot supplied with the terminal blocks).

10 AWG

Ordering details

1SNK161007F0014

Description

54.6 2.15"

47.1 1.85"

90°

180°

88.8 3.5"

90°

59.7 2.35"

Type
ZS4-SF1ZS4-SF1-OR

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthMain technical data

Pkg

Part Number

Grey, dark grey
Orange, dark
grey

Fuse

1SNK508410R0000
1SNK508430R0000

Weightqty(1 pce) g

50
50

13.30
13.30

Mounting instructions

1 conductor
per clamp

ZS4-SF1

96.3 3.79"

Color

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

8

3

4

5

6

1
2
3
4

Color

5

End stops
10 mm
End sections
1.5 mmLateral jumper bars 10 poles
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings

0.394 in0.059 in35 A (IEC)6

Neutral cartridge

5x25

7

Terminal block
markers

Blank marker
Blank card

White

Universal wire markers holder

Grey

Dark grey
Dark grey
Grey

Type

Part Number

Pkg

Weightqty(1 pce) g

14.00
1.80
5.00
1.00
1.50
2.00

BAM4
ES4-SFPC81-10
TGA8
TGA8
TGA8
ANT

1SNK900001R0000
1SNK508960R0000
1SNA173523R1100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400

50
20
10
10
10
10
10

CN5

1SNA179371R1600

10

3.9

1680
22
20
10

0.27
10.00
14.00
0.20

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161011S0201

7

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-SF1-T screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with test socket - 8 mm 0.315 in spacing
Description

4 mm²–– Protect your circuit with 5x25 and 5x20 fuse terminal blocks (fuse not supplied with the terminal blocks),–– Compliant with IEC 60947-7-3 standard,–– With built in test sockets.

10 AWG

1SNK161041F0014

Ordering details

47.1 1.85"

90°

180°

54.6 2.15"

90°

59.7 2.35"

88.8 3.5"

Color

With 2 test sockets DIA 2 mm 0.079 in

Type

Pkg

Part Number

Grey, dark grey

ZS4-SF1-T2

1SNK508411R0000

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthFuse

Main technical data

Weightqty(1 pce) g

50

13.30

Mounting instructions

1 conductor
per clamp

ZS4-SF1-T

96.3 3.79"

Description

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

Description

2

Color

3

4

1
2
3
4
5

End stops
10 mm
End sections
1.5 mmLateral jumper bars 10 poles
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings

5

6

6

Neutral cartridge

5x25

7

Terminal block
markers

Blank marker
Blank card

White

Universal wire markers holder

Grey

Dark grey
Dark grey
Grey

Part Number

Pkg

Weightqty(1 pce) g

14.00
1.80
5.00
1.00
1.50
2.00

BAM4
ES4-SFPC81-10
TGA8
TGA8
TGA8
ANT

1SNK900001R0000
1SNK508960R0000
1SNA173523R1100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400

50
20
10
10
10
10
10

CN5

1SNA179371R1600

10

3.9

1680
22
20
10

0.27
10.00
14.00
0.20

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161036S0201

7

0.394 in0.059 in35 A (IEC)

Type

Technical data valid for copper conductors only.

PAGE 269

ZS4-SF1-R screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator - 8 mm 0.315 in spacing
4 mm²
10 AWG

Description–– Protect your circuit with 5x25 and 5x20 fuse terminal blocks (fuse not supplied with the terminal blocks),–– Compliant with IEC 60947-7-3 standard,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
1SNK161042F0014

Description
Fuse

Color

With blown fuse indicator 115 … 250 V
AC / DC
With blown fuse indicator 24 … 110 V
AC / DCType

Grey, dark grey

47.1 1.85"

90°88.8 3.5"

54.6 2.15"

90°
96.3 3.79"

180°(1 pce) g

1SNK508414R0000

50

13.30

ZS4-SF1-R1

1SNK508412R0000

50

13.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

59.7 2.35"

Weightqty

ZS4-SF1-R3

Main technical data

ZS4-SF1-R

Pkg

Part Number

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 132.9 1.30"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

2

8

3

4

5

6

Description
1
2
3
4
5
6

Color

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A (IEC)
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
Grey

White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
ANT
1SNA168675R1400
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
1680
22
20
10

14.00
1.80
5.00
1.00
1.50
2.00
0.27
10.00
14.00
0.20

1SNK161034S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-SF1-R screw clamp terminal blocks
For 5 x 20 and 5 x 25 fuses - with blown fuse indicator and test sockets - 8 mm 0.315 in spacing
Description

4 mm²
10 AWG–– Protect your circuit with 5x25 and 5x20 fuse terminal blocks (fuse not supplied with the terminal blocks),–– Compliant with IEC 60947-7-3 standard,–– Ease the test with built-in test sockets,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

1SNK161043F0014

Ordering details
Description

Color

Type

Fuse With blown fuse indicator 115 … 250 V AC / DC Grey, dark grey
and 2 test sockets DIA 2 mm 0.079 inWith blown fuse indicator 24 … 110 V AC / DCand 2 test sockets DIA 2 mm 0.079 in

Pkg

Part Number
1SNK508415R0000

50

13.30

ZS4-SF1-R2

1SNK508413R0000

50

13.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15
11 mm
0.432 in

ZS4-SF1-R

1 conductor
per clamp

32.9 1.30"

47.1 1.85"

54.6 2.15"

90°

90°
88.8 3.5"

96.3 3.79"

180°(1 pce) g

ZS4-SF1-R4

Main technical data

59.7 2.35"

Weightqty

630 V
8000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
10 A / 10 AWG
Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

300 V
NEMA 18 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
Description

2

3

4

1
2
3
4

5

6

5
6

Color

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A (IEC)
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
Grey

White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
ANT
1SNA168675R1400
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
1680
22
20
10

14.00
1.80
5.00
1.00
1.50
2.00

8

0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161035S0201

1

Technical data valid for copper conductors only.

PAGE 271

ZS4-R1 screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

4 mm²

Simplify the alternated feed-through and fuse circuits operations:–– With the same profile as the ZS4-SF1, the wiring of the alternated feed-through and fuse circuits is easier.

10 AWG

Ordering details

1SNK161046F0014

Description
Feed-throughColor
Profile aligned with ZS4-SF1

Grey

32.9 1.30"

8 mm 0.315 in spacing

38.6 1.52"

46.1 1.82"

59.7 2.35"

ZS4-R1Main technical data

Pkg

Part Number
1SNK508013R0000

Weightqty(1 pce) g

50

11.00

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
24 A / 2.5 mm²
300 A

24 ... 10 AWG

Wire stripping
length800 V
6000 VIP20

300 V

1 conductor
per clamp
ZS4-R1Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
26 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

3

Description

2

4

1
2
3
4

Color

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A (IEC)
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
Grey
White

Universal wire markers holder

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
1680
22
20
10

14.00
1.80
5.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Fuse screw clamp terminal blocks
Description
Fuse

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color
Grey, dark greyType
ZS4-SF1

Part Number
1SNK508410R0000

Pkg

Weightqty(1 pce) g

50

13.30

1SNK161009S0201

8

Grey

Type

ZS4-S-R3 screw clamp terminal blocks
Disconnect with lever - 8 mm 0.315 in spacing
Description

4 mm²

Simplify the disconnect operations for the disconnect terminal blocks installed next to fuse terminal blocks ZS4-SF1:–– With the same profile as ZS4-SF1, the ZS4-S-R3 disconnect lever is easily operated by hand and the wiringof the alternated disconnect and fuse circuits is easier.,–– Neutral cartridge CN5 5x25 included.

10 AWG

1SNK161032F0014

Ordering details
Description
Disconnect

Color
Profile aligned with ZS4-SF1

Type

Grey, orange
Grey, blue

ZS4-S-R3ZS4-S-R3-T2

Main technical data

47.1 1.85"

90°88.8 3.5"

180°

54.6 2.15"

90°
96.3 3.79"

59.7 2.35"

1SNK508416R0000
1SNK508419R0000

Weightqty(1 pce) g

50
50

13.30
13.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
18 A / 2.5 mm²
18 A / 4 mm²
300 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 VIP20

300 V

1 conductor
per clamp

ZS4-S-R3

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.432 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG
18 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

TorqueNEMA 132.9 1.30"

8 mm 0.315 in spacing

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect lever does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

BV

EAC

DNV

Rina

Accessories
Description

2

3

4

5

6

1
2
3
4
5
6

Color

End stops
10 mm
0.394 inEnd sections
1.5 mm
0.059 in
Lateral jumper bars 10 poles
35 A (IEC)
Assembly rods
2 poles
3 poles
4 poles
Spring retaining Rings
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark grey
Grey

White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES4-SF
1SNK508960R0000
PC81-10
1SNA173523R1100TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
ANT
1SNA168675R1400
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
1680
22
20
10

14.00
1.80
5.00
1.00
1.50
2.00
8

0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Fuse screw clamp terminal blocks
Description
Fuse

Color
Grey, dark greyType
ZS4-SF1

Part Number
1SNK508410R0000

Pkg

Weightqty(1 pce) g

50

13.30

Technical data valid for copper conductors only.

PAGE 273

1SNK161044S0201

1

ZS4-SF screw clamp terminal blocks
For 5 x 20 fuses - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks.

Ordering details
1SNK161021F0014

Description

Color

ZS4-SF

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthMain technical data

86.3 3.40"

78.8 3.10"

70.3 2.77"

Pkg

Part Number

Grey, dark grey

Fuse

1SNK506410R0000

Weightqty(1 pce) g

50

18.60

Mounting instructions

1 conductor
per clamp
ZS4-SFType

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

150 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.

26.7 1.05"

6 mm 0.236 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

1
8

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

4

6

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK161005S0201

Accessories

ZS4-SF-T screw clamp terminal blocks
For 5 x 20 fuses - with test socket - 6 mm 0.236 in spacing
4 mm²

1SNK161038F0014

10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks,–– Ease the test with built-in test socket screws.

Ordering details
Description

Color

ZS4-SF-T2

1SNK506411R0000

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthMain technical data

86.3 3.40"

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG(1 pce) g

50

18.60

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

78.8 3.10"

70.3 2.77"

Weightqty

Mounting instructions

1 conductor
per clamp

ZS4-SF-T

Pkg

Part Number

Grey, dark grey

Fuse

With 2 test sockets DIA 2 mm 0.079 in

Type

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

150 V
NEMA 126.7 1.05"

6 mm 0.236 in spacing

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories

3

5

Description

2
1
2

End stops
Jumper bars

3
4
5

Test connectors
Spacers
Terminal block
markers

4

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card

Dark grey

Universal wire markers holder

Grey

OrangeDark grey
Dark grey
White

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
0.27
10.00
11.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
1SNK161038S0201

1

Technical data valid for copper conductors only.

PAGE 275

ZS4-SF-R screw clamp terminal blocks
For 5 x 20 fuses - with blown fuse indicator - 6 mm 0.236 in spacing
4 mm²

1SNK161039F0014

10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
Description
Fuse

Color

With blown fuse indicator 115 … 250 V
AC / DC
With blown fuse indicator 24 … 110 V
AC / DCType

Grey, dark grey

50

18.60

ZS4-SF-R1

1SNK506412R0000

50

18.60

Mounting instructions
IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
length86.3 3.40"

78.8 3.10"

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque26.7 1.05"

6 mm 0.236 in spacing(1 pce) g

1SNK506415R0000

Connecting capacity
1 conductor
per clamp

70.3 2.77"

Weightqty

ZS4-SF-R3

Main technical data
ZS4-SF-R

Pkg

Part Number

500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

150 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

Description

2

3

4

5

6

1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK161006S0201

8

CB

ZS4-SF-R screw clamp terminal blocks
For 5 x 20 fuses - with blown fuse indicator and test sockets - 6 mm 0.236 in spacing
4 mm²

1SNK161040F0014

10 AWG

Description–– Protect your circuits with 5x20 fuse terminal blocks compliant with IEC 60947-7-3 standard (fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels aligned with ZS4 or ZS4-R2 feed-through and
ZS4-S-R1 disconnect terminal blocks,–– Ease the test with built-in test socket screws,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
Description
Fuse

ZS4-SF-R

Color

With blown fuse indicator 115 … 250 V
AC / DC and 2 test sockets DIA 2 mm
0.079 inWith blown fuse indicator 24 … 110 V
AC / DC and 2 test sockets DIA 2 mm
0.079 inType

Grey, dark grey

Pkg

Part Number
1SNK506416R0000

50

18.60

ZS4-SF-R2

1SNK506413R0000

50

18.60

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthTH 35-7.5,
TH 35-15
10.5 mm0.412 in70.3 2.77"

86.3 3.40"

1 conductor
per clamp
78.8 3.10"(1 pce) g

ZS4-SF-R4

Main technical data

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
10 A / 10 AWG

26.7 1.05"

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque6 mm 0.236 in spacing

Weightqty

500 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

150 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

8

Rina

1

3

5

Description

2
1
2

End stops
Jumper bars

3
4
5

Test connectors
Spacers
Terminal block
markers

4

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card

Dark grey

Universal wire markers holder

Grey

OrangeDark grey
Dark grey
White

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

PAGE 277

1SNK161037S0201

Accessories

ZS4-R2 screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing
Description

4 mm²–– Simplify the distribution of circuits in marshalling cabinets thanks to our feed-through terminal blocks withthe same profile as ZS4-SF fuse, ZS4-S-R1 disconnect and ZS4-PE-R2 ground terminal blocks: aligned
conductor entries, jumper channels and marking in just 6 mm 0.236 in spacing,–– No end section needed: closed block.

10 AWG

1SNK161074V0014

Ordering details
Description
Feed-through

Color

Type

Profile aligned with ZS4-SF and
ZS4-S-R1

Grey

ZS4-R2Main technical data

48.8 1.92"

56.3 2.22"

70.5 2.77"

1SNK506013R0000

Pkg

Weightqty(1 pce) g

50

12.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

1 conductor
per clamp

ZS4-R2

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
30 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

TorqueNEMA 126.7 1.05"

6 mm 0.236 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2

3

5

6

3
4
5
6
7

7

10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)
Cross spacing jumpers 3 poles
32 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
End module, 5.2 mm 0.205 inSpacers
0.8 mm
0.031 inTerminal block
Blank marker
markers
Blank card
End stops
Jumper bars

Universal wire markers holder

Dark grey
OrangeOrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
JB85-3
1SNK900603R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
10
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
2.80
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Screw clamp terminal blocks
Description
Fuse
ZS4-SFZS4-S-R1

Disconnect

Color
Profile aligned with ZS4-R2 andZS4-PE-R2
Profile aligned with ZS4-R2 andZS4-PE-R2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Type

Grey, dark grey
Grey

Part Number

Pkg

Weightqty(1 pce) g

ZS4-SF

1SNK506410R0000

50

18.60

ZS4-S-R1

1SNK506310R0000

50

13.20

1SNK161083S0201

8

4

Color

ZS4-PE-R2 screw clamp terminal blocks
Ground - 6 mm 0.236 in spacing
Description

4 mm²

Simplify the shielding connection of your analog circuits in marshalling cabinets thanks to our ground terminal
blocks with the same profile as ZS4-SF fuse, ZS4-S-R1 disconnect and ZS4-R2 feed-through terminal blocks.

10 AWG

Ordering details
1SNK161089V0014

Description

Color
Screwless rail connection

GroundType

Green-yellow

ZS4-PE-R2

1SNK506153R0000

IEC

UL - CSA

Rail

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A3-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data

ZS4-PE-R2

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

25

15.30

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG
396 A

Protection

IP20

NEMA 1

TH 35-7.5,
TH 35-15
10.5 mm0.413 inØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque48.8 1.92"

56.3 2.22"

Weight(1 pce) g

Flat screwdriverTool
77 3.03"26.7 1.05"

Pkg
qty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing

CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

Color

End stops
End sections
Terminal block
markers

10 mm
0.394 in
2.2 mm0.087 in
Blank marker
Blank card

Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES6-4S
1SNK505911R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
1680
22
20
10

14.00
3.10
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

Screw clamp terminal blocks
Fuse
ZS4-SFZS4-S-R1

Disconnect

Color
Profile aligned with ZS4-R2 andZS4-PE-R2
Profile aligned with ZS4-R2 andZS4-PE-R2

Type

Grey, dark grey
Grey

Part Number

Pkg

Weightqty(1 pce) g

ZS4-SF

1SNK506410R0000

50

18.60

ZS4-S-R1

1SNK506310R0000

50

13.20

Technical data valid for copper conductors only.

PAGE 279

1SNK161079S0201

Description

ZS4-S-R2 screw clamp terminal blocks
Disconnect with lever - 6 mm 0.236 in spacing
4 mm²
10 AWG

Description
Simplify the disconnect operations for the disconnect terminal blocks installed next to fuse terminal blocks ZS4-SF:–– With the same profile as ZS4-SF, the ZS4-S-R2 disconnect lever is easily operated by hand and the wiringof the alternated disconnect and fuse circuits is easier.

Ordering details
1SNK161033F0014

Description

Color
Profile aligned with ZS4-SF

Disconnect

Grey, orange

86.3 3.40"
26.7 1.05"

6 mm 0.236 in spacing

78.8 3.10"

70.3 2.77"

ZS4-S-R2

Main technical data

Pkg

Part Number
1SNK506414R0000

Weightqty(1 pce) g

50

21.6

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
18 A / 2.5 mm²
18 A / 4 mm²
300 A

24 ... 10 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

400 V
6000 VIP20

150 V

1 conductor
per clamp
ZS4-S-R2

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.412 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
13 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

TorqueNEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect lever does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Rina

Accessories
1

3

5

1
2

End stops
Jumper bars

3

Test adapters

4
5
6

Test connectors
Spacers
Terminal block
markers

4

6

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
50
20
20
20
10
10
1680
22
20
10

14.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Fuse screw clamp terminal blocks
Description
Fuse

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color
Grey, dark greyType
ZS4-SF

Part Number
1SNK506410R0000

Pkg

Weightqty(1 pce) g

50

18.60

1SNK161043S0201

8

Description2

ZS10-SF screw clamp terminal blocks
For 6.3x32 fuses - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Protect your circuits with 6.3x32 (¼ x 1¼ in) fuse terminal blocks compliant with IEC 60947-7-3 standard(fuse not supplied with the terminal blocks),–– Simplify the distribution thanks to the two jumper channels.

Ordering details
1SNK161071F0014

Description

Color

ZS10-SF

1SNK508418R0000

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
10 A / 10 mm²

24 ... 6 AWG

Wire stripping
lengthMain technical data

74.3 2.93"

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

85.3 3.36"

Weight(1 pce) g

50

28.50

630 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
22 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque77.8 3.06"

Pkg
qty

Mounting instructions

1 conductor
per clamp
ZS10-SF

Part Number

Grey, dark grey

Fuse

Closed block

Type

600 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

26.7 1.05"

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

8 mm 0.315 in spacing

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

Overload and short-circuit
protection

4W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

2.5 W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

DNV

Accessories
Description

2
1
2

3

4

5

6

End stops
Jumper bars

3

Test adapters

4

Test connectors

56Spacers
Terminal block
markers

Color
10 mm
0.394 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
2.8 mm0.110 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
40
20
20
20
10
10
10
1680
22
20
10

14.00
2.70
4.10
5.60
7.00
14.20
1.70
2.40
5.20
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161052S0201

1

Technical data valid for copper conductors only.

PAGE 281

ZS10-SF-R screw clamp terminal blocks
For 6.3x32 fuses - with blown fuse indicator - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description–– Protect your circuits with 6.3x32 (¼ x 1¼ in) fuse terminal blocks compliant with IEC 60947-7-3 standard(fuse not supplied with the terminal blocks),–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leakage current < 0.5 mA).

Ordering details
1SNK161073F0014

Description
Fuse

Color

With blown fuse indicator 115 … 250 V
AC / DC
With blown fuse indicator 24 … 110 V
AC / DCType

Grey, dark grey

8 mm 0.315 in spacing

77.8 3.06"

85.3 3.36"
26.7 1.05"

50

30.50

ZS10-SF-R1

1SNK508421R0000

50

30.50

Mounting instructions
IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
10 A / 10 mm²

24 ... 6 AWG

Wire stripping
length24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

630 V
6000 V
IP20

Rated voltage
Impulse withstand voltage
Protection

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
22 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque600 V
NEMA 1

Mount your fuse safely without touching any active part: put the fuse into the hooks of the fuse holder shutter;at the closing of the shutter, the fuse is perfectly in place in the fuse holder.
Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement
1

Weight(1 pce) g

1SNK508422R0000

Connecting capacity
1 conductor
per clamp

74.3 2.93"

Pkg
qty

ZS10-SF-R3

Main technical data

ZS10-SF-R

Part Number

Assembly composed of 5 fuse terminal blocks

2

Overload and short-circuit
protection

4W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

2.5 W

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

3

4

CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Description
8

5

6

1
2

End stops
Jumper bars

3

Test adapters

4

Test connectors

56Spacers
Terminal block
markers

Color
10 mm
0.394 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
2.8 mm0.110 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
40
20
20
20
10
10
10
1680
22
20
10

14.00
2.70
4.10
5.60
7.00
14.20
1.70
2.40
5.20
5.20
1.40
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK161053S0201

Accessories

ZS10-S-R2 screw clamp terminal blocks
Disconnect with lever - 8 mm 0.315 in spacing
10 mm²
6 AWG

Description
Simplify the disconnect operations for the disconnect terminal blocks installed next to fuse terminal blocks ZS10-SF:–– With the same profile as ZS10-SF, the ZS10-S-R2 disconnect lever is easily operated by hand and the wiringof the alternated disconnect and fuse circuits is easier.

Ordering details
1SNK161070F0014

Description

Color
Profile aligned with ZS10-SF

Disconnect

Grey, orange

ZS10-S-R2

Main technical data

ZS10-S-R2

77.8 3.06"

74.3 2.93"

Part Number
1SNK508417R0000

Pkg

Weightqty(1 pce) g

50

35.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Maximum current / Maximum cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
10 A / 4 mm²
25 A / 10 mm²
480 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
6000 VIP20

600 V

1 conductor
per clamp

85.3 3.36"

Type

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 4 mmØ 0.157 in

20 ... 12 AWG
22 A / 25 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

TorqueNEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect lever does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.

26.7 1.05"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4

Test connectors

56Spacers
Terminal block
markers

4

6

Color
10 mm
0.394 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in
2.8 mm0.110 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
50
50
50
40
20
20
20
10
10
10
1680
22
20
10

14.00
2.70
4.10
5.60
7.00
14.20
1.70
2.40
5.20
5.20
1.40
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Fuse screw clamp terminal blocks
Description
Fuse

Color
Closed block

Grey, dark grey

Type
ZS10-SF

Part Number
1SNK508418R0000

Pkg

Weightqty(1 pce) g

50

28.50

Technical data valid for copper conductors only.

PAGE 283

1SNK161055S0201

1

ZS4-D2 screw clamp terminal blocks
Double deck with 2 feed-through circuits - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 5.2 mm 0.205 in spacing,–– Customize yourself the ZS4-D2 by soldering electronic components (up to 8.8 mm x 3.2 mm 0.346 x 0.125in) in the existing linking bars punching.

Ordering details
1SNK161014F0014

Description
Feed-throughColor
2 feed-through circuits

Grey
Blue
Orange36.8 1.45"

67 2.64"74.5 2.94"

70.4 2.77"

Pkg

Part Number

ZS4-D2ZS4-D2-BL
ZS4-D2-OR

Main technical data

1SNK505210R0000
1SNK505220R0000
1SNK505230R0000

Weightqty(1 pce) g

50
50
50

15.30
15.30
15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 20 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS4-D2Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

5.2 mm 0.205 in spacing

CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

3

4

5

6

7

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161003S0201

8

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-D1 screw clamp terminal blocks
Double deck with 1 feed-through circuit - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description–– Ease one potential distribution on 4 independent screw clamps,–– Save space by connecting conductors up to 4 mm² (CB certified) 12 AWG in just 5.2 mm 0.205 in spacing.

Ordering details
Description
1SNK161015F0014

Feed-throughColor
1 feed-through circuit

Grey

67 2.64"74.5 2.93"

70.4 2.77"

Pkg

Part Number

ZS4-D1

1SNK505211R0000

Main technical data

Weightqty(1 pce) g

50

15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 29 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 20 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS4-D1Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Flat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

36.8 1.45"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161007S0201

1

Technical data valid for copper conductors only.

PAGE 285

ZS6-D2 screw clamp terminal blocks
Double deck with 2 feed-through circuits - 6 mm 0.236 in spacing
6 mm²

1SNK161010F0014

10 AWG

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 6 mm 0.236 in spacing,–– Customize yourself the ZS6-D2 by soldering electronic components (up to 8.8 mm x 3.2 mm 0.346 x 0.125in) in the existing linking bars punching,–– Boost the performances: ZS6-D... with ES4-D2 end section is rated 1000 V DC IEC, perfectly adapted tosolar applications.

Ordering details
Description
Feed-throughColor
2 feed-through circuits

Type

Grey
Blue
OrangeYellow
Red
White
Black

ZS6-D2ZS6-D2ZS6-D2-BL
ZS6-D2-OR
ZS6-D2-YL
ZS6-D2-RD
ZS6-D2-WH
ZS6-D2-BK

Main technical data
70.4 2.77"

67 2.64"74.5 2.94"

6 mm 0.236 in spacing

1SNK506210R0000
1SNK506220R0000
1SNK506230R0000
1SNK506260R0000
1SNK506262R0000
1SNK506265R0000
1SNK506266R0000

Weightqty(1 pce) g

50
50
50
50
50
50
50

18.40
18.40
18.40
18.40
18.40
18.40
18.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
40 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 40 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 30 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

36.8 1.45"

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories
1

Description

2

3

4

5

6

1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5
6
7
8

Test connectors
Spacers
Shield connectors
Terminal block
Blank marker
markers
Blank card

8

7

8

Color
10 mm
0.394 in2.55 mm0.100 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
SHB
1SNK900602R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
20
20
20
10
10
20
1680
22
20
10

24.00
4.10
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
4.90
0.27
10.00
11.00
0.20

Ground screw clamp terminal blocks
Description
GroundProfile aligned with ZS6-D2 and ZS6-D1

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSColorGreen-yellow

Type
ZS6-D1-PE

Part Number
1SNK506250R0000

Pkg

Weightqty(1 pce) g

20

18.40

1SNK161014S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

ZS6-D1 screw clamp terminal blocks
Double deck with 1 feed-through circuit - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description–– Ease one potential distribution on 4 independent screw clamps,–– Save space by connecting conductors up to 6 mm² 10 AWG in just 6 mm 0.236 in spacing,–– Boost the performances: ZS6-D... with ES4-D2 end section is rated 1000 V DC IEC, perfectly adapted tosolar applications.

1SNK161009F0014

Ordering details
Description
Feed-through

Color

Type

1 feed-through circuit

Grey
Red

ZS6-D1ZS6-D1-RD

1SNK506211R0000
1SNK506214R0000

Main technical data

36.8 1.45"

67 2.64"74.5 2.93"

70.4 2.77"

Weightqty(1 pce) g

50
50

18.40
18.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
40 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
lengthIncreased safety Ex e

440 V 40 A IEC/EN 60079-7 - IM2 II 2 GD Ex eb I/II/IIIC – 300 V 30 A UL 60079-7 - Class I, Zone 1, AEx e II, Ex e II U

1 conductor
per clamp

ZS6-D1

Pkg

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

Flat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque100 kA
300 V

800 V
8000 VIP20

TH 35-7.5,
TH 35-15
10 mm
0.393 in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing

CE

CB

RoHS

USR CNRCSAEAC Ex

ATEX

IECEx

BR-Ex e II

Haz Loc

BV

DNV

Rina

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in4

Test adapters

5
6
7
8

Test connectors
Spacers
Shield connectors
Terminal block
Blank marker
markers
Blank card

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
SHB
1SNK900602R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
20
20
20
10
10
20
1680
22
20
10

24.00
4.10
1.30
2.10
2.90
3.60
7.40
1.70
2.40
5.20
0.80
4.90
0.27
10.00
11.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161013S0201

1

Technical data valid for copper conductors only.

PAGE 287

ZS6-D2-PE screw clamp terminal blocks
Double deck with 1 feed-through circuit and 1 ground circuit - 6 mm 0.236 in spacing
Description

6 mm²–– Save space with ZS6-D2-PE terminal blocks: 1 feed-through circuit and 1 ground circuit in just 6 mm 0.236
in spacing,–– Customize yourself the ZS6-D2-PE terminal blocks by soldering electronic components (up to 8.8 mm x
3.2 mm 0.346 x 0.125 in) in the existing linking bars punching.

10 AWG

1SNK161061F0014

Ordering details
Description

Color

Type

Feed-through + 1 feed-through circuit and 1 groundcircuitgroundGrey

ZS6-D2-PE

Main technical data

36.8 1.45"

6 mm 0.236 in spacing

67 2.64"74.5 2.94"

77.1 3.03"

1SNK506212R0000

Pkg

Weightqty(1 pce) g

50

18.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²0.22 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²
41 A / 6 mm²
720 A

24 ... 10 AWG

Wire stripping
length800 V
8000 VIP20

300 V

1 conductor
per clamp

ZS6-D2-PE

Part Number

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
10 mm
0.393 inFlat screwdriverToolØ 4 mmØ 0.157 in

24 ... 14 AWG
30 A / 10 AWG

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

TorqueNEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

3

4

5

6

1
2
3

End stops
End sections
Jumper bars

4
5
6
7

Test adapters
Test connectors
Spacers
Terminal block
markers

7

Color
10 mm
0.394 in2.55 mm0.100 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 4 mm 0.157 in
End module, 5.2 mm 0.205 in
0.8 mm
0.031 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP4
1SNK900205R0000
TC5-R1
1SNK900201R0000
ES-TC6
1SNK900105R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
20
20
10
10
1680
22
20
10

24.00
4.10
1.30
2.10
2.90
3.60
7.40
2.40
5.20
0.80
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Feed-through screw clamp terminal blocks
Description
Feed-throughColor
2 feed-through circuits

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Type
Grey

ZS6-D2

Part Number
1SNK506210R0000

Pkg

Weightqty(1 pce) g

50

18.40

1SNK161048S0201

8

Description2

ZS6-D1-PE screw clamp terminal blocks
Double deck with 1 ground circuit - 6 mm 0.236 in spacing
6 mm²
10 AWG

Description–– Save space with double deck ground terminal blocks aligned with ZS6-D2 double deck terminal blocks forconvenient cabling process and circuit configuration,–– Benefit from our screwless rail connection: non operator independant, secured snap on or remove from therail, performances above the requirements of IEC 60947-7-2 standard.

1SNK161062F0014

Ordering details
DescriptionColor
1 ground circuit

GroundType

Green-yellow

ZS6-D1-PE

1SNK506250R0000

IEC

UL - CSA

Rail

0.2 ... 6 mm²0.22 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²
A4-B3

24 ... 10 AWG

Wire stripping
lengthMain technical data

ZS6-D1-PE

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 12 AWG
24 ... 12 AWG

20

18.40

Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

10 AWG

Protection

IP20

NEMA 1

TH 35-7.5,
TH 35-15
10 mm
0.393 in

Ø 4 mmØ 0.157 in

0.85 Nm ± 0.15
7.52 lb.in ± 1.33

Torque67 2.64"74.5 2.94"

Weight(1 pce) g

Flat screwdriver

Tool
77.1 3.03"

36.8 1.45"

Pkg
qty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Number

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

6 mm 0.236 in spacing

CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

10 mm
0.394 in2.55 mm0.100 in
Blank marker
Blank card
Universal wire markers holder

Dark grey
Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
MG-CPM 13 41791 1SNB041791R0612
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
1680
22
20
10

24.00
4.10
0.27
10.00
11.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

8

1SNK161049S0201

3

End stops
End sections
Terminal block
markers

Color

Technical data valid for copper conductors only.

PAGE 289

ZS4-D2-S screw clamp terminal blocks
Double deck with 1 disconnect circuit and 1 feed-through circuit - 5.2 mm 0.205 in spacing
4 mm²
10 AWG

Description–– Save space: connect one complete circuit on a single block featuring disconnect and feed-through for the
return circuit in just 5.2 mm 0.205 in spacing,–– Same profile as ZS4-D... double deck terminal blocks: convenient cabling process, aligned jumpers, markers and common end section.

1SNK161095V0014

Ordering details
Description

Color

Feed-through + 1 disconnect circuit and 1 feedthrough circuit
disconnect

77.3 3.04"

71.1 2.8"

84.8 3.34"

78.6 3.09"

70.4 2.77"

Grey

ZS4-D2-S

Main technical data

Part Number
1SNK505315R0000

Pkg

Weightqty(1 pce) g

50

15.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²

24 ... 10 AWG

Wire stripping
length25 A / 4 mm²

27 A / 10 AWG

29 A / 4 mm²
480 A
630 V
8000 V
IP20

27 A / 10 AWG

1 conductor
per clamp

ZS4-D2-SType

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 136.8 1.45"

5.2 mm 0.205 in spacing

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

Description

2

3

4

5

6

Color

1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5
6

Shield connectors
Terminal block
Blank marker
markers
Blank card

8

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
SHB
1SNK900602R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
20
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
4.90
0.23
9.00
10.00
0.20

1SNK161074S0201

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-D2-S-T screw clamp terminal blocks

Double deck with 1 disconnect circuit with test socket screws and 1 feed-through circuit - 5.2 mm 0.205 in spacing

4 mm²
10 AWG

Description
Find the same functionalities as ZS4-D2-S, upgraded with the two built-in test socket screws meant to ease
your signal testing during commissioning and maintenance.

Ordering details

1SNK161099V0014

Description

Color

Feed-through + 1 disconnect circuit with 2 test
socket screws and 1 feed-throughdisconnect
circuit36.77 1.45"

5.2 mm 0.205 in spacing

77.3 3.04"

71.1 2.8"

84.8 3.34"

78.6 3.09"

70.4 2.77"

Grey

ZS4-D2-S-T2

Main technical data

Part Number
1SNK505316R0000

Pkg

Weightqty(1 pce) g

50

16.20

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²

24 ... 10 AWG

Wire stripping
length25 A / 4 mm²

27 A / 10 AWG

29 A / 4 mm²
480 A
630 V
8000 V
IP20

27 A / 10 AWG

1 conductor
per clamp
ZS4-D2-S-T

Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

Recommendation for best usage: in horizontal assemblies, disconnect terminal blocks should be mountedwith fixed foot on top (power side) so that the disconnect knife does not partially close through gravity.
Furthermore, as specified per IEC 60947-7-1, disconnect terminal blocks are intended to be used for temporary
disconnection at zero potential and at no load.
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
Description

2

3

4

5

6

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

4

Test adapters

5
6

Shield connectors
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
SHB
1SNK900602R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
20
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
4.90
0.23
9.00
10.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161075S0201

1

Technical data valid for copper conductors only.

PAGE 291

ZS4-D2-SF1 screw clamp terminal blocks
Double deck with 1 fuse circuit and 1 feed-through circuit - 8 mm 0.315 in spacing
Description

4 mm²–– Save space: connect one complete circuit on a single block featuring fuse and feed-through for the return circuit,–– Protect your circuit with either 5X20 or 5X25 fuse (fuse not supplied with the terminal blocks),–– High performances product: compliant with IEC 60947-7-3 standard and jumper channel for the feedthrough circuit.

10 AWG

Ordering details
1SNK161096V0014

Description

Color

ZS4-D2-SF1

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section

0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²

24 ... 10 AWG

Wire stripping
length

6.3 A / 4 mm²

12 A / 10 AWG

32 A / 4 mm²

30 A / 10 AWG

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

Main technical data

89.2 3.51"

83 3.27"
68 2.68"

124.7 4.91"
109.7 4.32"

90°
90°

180°

1SNK508425R0000

Pkg

Weightqty(1 pce) g

50

27.50

Mounting instructions

1 conductor
per clamp

ZS4-D2-SF1

Part Number

Grey, dark grey

Feed-through+ fuse1 fuse circuit and 1 feed-throughcircuitType

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG

Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

NEMA 1

48.2 1.90"

8 mm 0.315 in spacing

Separatearrangement

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

1

8

Description

2
1
2
3

3

4

5

6

4
5
6

7

9

8

7
8
9

Color

10 mm
0.394 in
2.5 mm
0.098 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)
Lateral jumper bars 10 poles
35 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 inSpacers
2.8 mm0.110 in
Assembly rods
2 poles
3 poles
4 poles
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeGrey
Dark grey
Dark grey
Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2-SF1
1SNK508911R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
PC81-10
1SNA173523R1100
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
40
20
10
20
20
10
10
10
10
10
10
1680
22
20
10

24.00
5.00
2.70
4.10
5.60
7.00
14.20
5.00
1.70
2.40
5.20
5.20
1.40
1.00
1.50
2.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK161076S0201

Accessories

ZS4-D2-SF1-R screw clamp terminal blocks
Double deck with 1 fuse circuit with blown fuse indicator and 1 feed-through circuit - 8 mm 0.315 in spacing
Description

4 mm²–– Find the same functionalities as ZS4-D2-SF1, upgraded with our integrated blown fuse indicator (with leakage current < 0.5 mA),–– Only one part number needed to fit AC / DC 24 V up to 110 V.

10 AWG

Ordering details

1SNK161097V0014

Description
Feed-through+ fuse

Color

Type

Grey, dark grey
1 fuse circuit with blown fuseindicator 115 ... 250 V AC / DC and
1 feed-through circuit
1 fuse circuit with blown fuseindicator 24 ... 110 V AC / DC and 1
feed-through circuit

83 3.27"
68 2.68"

124.7 4.91"
109.7 4.32"

90°
90°

180°

48.2 1.90"

8 mm 0.315 in spacing

50

29.40

ZS4-D2-SF1-R1

1SNK508423R0000

50

29.40

Mounting instructions
IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Disconnect circuit
Rated current / Rated cross section
Feed-through circuit
Rated current / Rated cross section

0.2 ... 6 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²0.22 ... 2.5 mm²

24 ... 10 AWG

Wire stripping
length

6.3 A / 4 mm²

12 A / 10 AWG

32 A / 4 mm²

30 A / 10 AWG

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 VIP20

300 V

Separatearrangement

24 ... 12 AWG
24 ... 12 AWG
24 ... 14 AWG

TH 35-7.5,
TH 35-15
11 mm
0.433 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 14 AWG

Torque0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

1.6 W

Exclusive short-circuit protection

4W

NEMA 1

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Weight(1 pce) g

1SNK508424R0000

Connecting capacity
1 conductor
per clamp

89.2 3.51"

Pkg
qty

ZS4-D2-SF1-R3

Main technical data
ZS4-D2-SF1-R

Part Number

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

BV

EAC

DNV

Accessories
Description

2
1
2
3

3

4

5

6

4
5
6

7

9

8

7
8
9

Color

10 mm
0.394 in
2.5 mm
0.098 in
2 poles
57 A (IEC)3 poles
57 A (IEC)4 poles
57 A (IEC)
5 poles
57 A (IEC)
10 poles
57 A (IEC)
Lateral jumper bars 10 poles
35 A (IEC)
Test adapters
For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
Test connectors
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 inSpacers
2.8 mm0.110 in
Assembly rods
2 poles
3 poles
4 poles
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeGrey
Dark grey
Dark grey
Dark grey

White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2-SF1
1SNK508911R0000
JB8-2
1SNK908302R0000
JB8-3
1SNK908303R0000
JB8-4
1SNK908304R0000
JB8-5
1SNK908305R0000
JB8-10
1SNK908310R0000
PC81-10
1SNA173523R1100
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
ES-TC8
1SNK900104R0000
TGA8
1SNA168672R1100TGA8
1SNA168673R1200TGA8
1SNA168674R1300
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
40
20
10
20
20
10
10
10
10
10
10
1680
22
20
10

24.00
5.00
2.70
4.10
5.60
7.00
14.20
5.00
1.70
2.40
5.20
5.20
1.40
1.00
1.50
2.00
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

PAGE 293

8

1SNK161077S0201

1

ZS4-T3 screw clamp terminal blocks
Triple deck with 3 feed-through circuits - 5.2 mm 0.205 in spacing
Description

4 mm²
12 AWG

Save space: 3 independent circuits in just 5.2 mm 0.205 in spacing,–– Fit many applications: space constraints, multiple signals distribution, sensors distribution, thanks to thejumper channels available on each deck.

Ordering details
1SNK161087V0014

Description
Feed-throughColor
3 feed-through circuits

Grey

55.3 2.17"

5.2 mm 0.205 in spacing

79.9 3.14

87.4 3.44"

100.1 3.94"

ZS4-T3Main technical data

Part Number
1SNK505212R0000

Pkg

Weightqty(1 pce) g

25

24.40

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²

24 ... 12 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp
ZS4-T3Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
20 A / 12 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories
1

3

4

5

6

1
2
3

End stops
End sections
Jumper bars

4

Test adapters

5
6

Label holders
Terminal block
markers

Color
10 mm
0.394 in
0.8 mm
0.031 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

Dark grey
Dark grey
OrangeDark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-T3
1SNK505961R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
100
1960
22
20
10

24.00
4.20
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161072S0201

8

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-T3-R1 screw clamp terminal blocks
Triple deck with 3 feed-through circuits - 6 mm 0.236 in spacing
Description

4 mm²
10 AWG

Unique triple deck solution combining increased connecting capacity ( up to 4 mm² with ferrule) and jumper
channel available on each deck,–– Fit many applications: space constraints, multiple signals distribution, sensors distribution,–– Closed terminal block: no end section needed, optimized rigidity.

1SNK161088V0014

Ordering details
Description
Feed-through

Color
Closed block with 3 feed-throughcircuits

87.4 3.44"

79.9 3.14"

100.1 3.94"

Grey

Part Number

ZS4-T3-R1

1SNK506213R0000

Main technical data

Pkg

Weightqty(1 pce) g

50

28.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
32 A / 4 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

480 A

Rated voltage
Impulse withstand voltage
Protection

800 V
8000 V
IP20

1 conductor
per clamp

ZS4-T3-R1

Type

24 ... 12 AWG
24 ... 12 AWG
24 ... 16 AWG

TH 35-7.5,
TH 35-15
10.5 mm0.413 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

24 ... 16 AWG
30 A / 10 AWG

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

Torque300 V
NEMA 1

55.3 2.17"

6 mm 0.236 in spacing
The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR

CSA

EAC

BV

DNV

Accessories

3

5

Description

2
1
2

End stops
Jumper bars

3

Test adapters

4
5

Label holders
Terminal block
markers

4

Color
10 mm
0.394 in
2 poles
41 A (IEC)3 poles
41 A (IEC)4 poles
41 A (IEC)
5 poles
41 A (IEC)
10 poles
41 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in

Dark grey
OrangeDark grey
Dark grey

Blank marker
Blank card

White

Universal wire markers holder

Grey

Type

Part Number

BAZH1
1SNK900102R0000
JB6-2
1SNK906302R0000
JB6-3
1SNK906303R0000
JB6-4
1SNK906304R0000
JB6-5
1SNK906305R0000
JB6-10
1SNK906310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
LH-J
1SNK900606R0000
MG-CPM 13 41791 1SNB041791R0612
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
50
50
50
50
20
20
20
100
1680
22
20
10

24.00
1.30
2.10
2.90
3.60
7.40
1.70
2.40
0.73
0.27
9.00
10.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161073S0201

1

Technical data valid for copper conductors only.

PAGE 295

ZS4-D-CH-UD screw clamp terminal blocks
Component holder - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details
Description

1SNK161141V0014

Component
holderColor
Cathode of the blocking diodeconnected to the lower circuit

Grey

67 2.64"74.5 2.94"

70.4 2.77"

ZS4-D-CH-UD

Main technical data

Part Number
1SNK505214R0000

Pkg

Weightqty(1 pce) g

50

15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
length

800 V

300 V

IP20

NEMA 1

1 conductor
per clamp

ZS4-D-CHType

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 12 AWG
TorqueTH 35-7.5,
TH 35-15
10 mm
0.393 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

36.8 1.45"

5.2 mm 0.205 in spacing

Accessories
1

3

4

5

6

7

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161090S0201

8

Description

2

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSZS4-D-CH-DU screw clamp terminal blocks
Component holder - 5.2 mm 0.205 in spacing
4 mm²
12 AWG

Description
Protect your circuit with one 1N4007 diode.

Ordering details
Description

1SNK161142V0014

Component
holderColor
Cathode of the blocking diodeconnected to the upper circuit

Grey

67 2.64"74.5 2.94"

70.4 2.77"

Part Number

ZS4-D-CH-DU

1SNK505215R0000

Main technical data

Pkg

Weightqty(1 pce) g

50

15.30

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²0.22 ... 4 mm²0.22 ... 4 mm²0.22 ... 2.5 mm²A3-B3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²0.22 ... 1.5 mm²
29 A / 4 mm²
480 A

24 ... 12 AWG

Wire stripping
length

800 V

300 V

IP20

NEMA 1

1 conductor
per clamp

ZS4-D-CHType

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 16 AWG
20 A / 12 AWG
TorqueTH 35-7.5,
TH 35-15
10 mm
0.393 inFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.6 Nm ± 0.1
5.31 lb.in ± 0.885

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

RoHS

USR CNR

CSA

EAC

36.8 1.45"

5.2 mm 0.205 in spacing

Accessories

3

4

5

6

7

Description

2

8

Color

1
2
3

End stops
End sections
Jumper bars

10 mm
0.394 in2.55 mm0.100 in
2 poles
32 A (IEC)3 poles
32 A (IEC)4 poles
32 A (IEC)
5 poles
32 A (IEC)
10 poles
32 A (IEC)
50 poles
32 A (IEC)For test plugs DIA 2 mm 0.079 in
For test plugs DIA 4 mm 0.157 in
5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

4

Test adapters

5

Test connectors

6
7
8

Shield connectors
Label holders
Terminal block
Blank marker
markers
Blank card
Universal wire markers holder

Dark grey
Dark grey
OrangeDark grey
Dark grey

Dark grey
White

Grey

Type

Part Number

BAZH1
1SNK900102R0000
ES4-D2
1SNK505960R0000
JB5-2
1SNK905302R0000
JB5-3
1SNK905303R0000
JB5-4
1SNK905304R0000
JB5-5
1SNK905305R0000
JB5-10
1SNK905310R0000
JB5-50
1SNK905350R0000
TP2
1SNK900203R0000
TP4
1SNK900205R0000
TC5
1SNK900200R0000
TC5-R1
1SNK900201R0000
SHB
1SNK900602R0000
LH-J
1SNK900606R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

20
20
50
50
50
50
30
10
20
20
10
10
20
100
1960
22
20
10

24.00
4.10
1.30
2.00
2.70
3.50
7.10
36.00
1.70
2.40
5.20
5.20
4.90
0.73
0.23
9.00
10.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161091S0201

1

Technical data valid for copper conductors only.

PAGE 297

SNK series, terminal blocks
Screw clamp technology - Test & measurement

Secure your measurement operations
The new ZS10-ST test & measurement terminal blocks benefit fromour long experience in the energy applications and from the SNKfeatures: performances, ergonomy, common
accessories and marking.

High performances– – 10 mm² 6 AWG– – 6 mm² 10 AWG with ferrule– – 50 A (IEC) 53 A (UL– – Worldwide certifications

RoHS

BV

EAC

Rely on our smart design
Insulated short circuit bridges:
SC-JB8Insulated captive test sockets:
AJS9
6 colorscompatible with standard
DIA. 4 mm test plugs(IEC 60010-031)

Circuit separators: CS
For visual separation between
CT & PT circuits

8

Protecting cover kits: KCO

New ground terminal block:

Lateral jumper bar: PC8
For CT or PT commoning

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160057S0201

ZS10-PE-R1

Guarantee accessonly to authorized operators

cover can be permanently sealed with a seal or cable tie.
Centering drilling guide for seal or cable tie.
The cover is specially designed to ease its mounting or removal:– – Hook shape on each side for convenient removal with screwdriver

Assembly with protecting cover

Drilling and centering guide

Seal with cable tie

Convenient removal with screwdriver

CT sidePT sidesliding link status: closed

Disconnect sliding link status:
Open and close symbols help tovisualize the sliding link position

sliding link status: opened
8

Measuring equipment side

1 Fully operated by screwdriver (DIA 3.5 mm)
2 Short-circuited position secured thanks to AJS9 test sockets tightening
3 Adapted hook shape maintain the bridge on terminal block in the1

2

3

non connected position

PAGE 299

1SNK160057S0201

Short-circuit CT circuits safely andconveniently

SNK series, terminal blocks
Test & measurement - Typical schematic for measuring devices

Common point on the transformers
CT's
P1

L1
P1

L2
L3

PT's

P1
S1

P2 S1

P2 S1

P2
S2

S2

S2

P

P

P

S

S

S

1

2

3

N

N

Voltage inputs
Measuring devices(ie: meters, protection relays…)

Current inputs

Bill of material with convenient customization(test sockets, feed-through terminals…)

Bill of material optimized

CT's

PT's

CT's

PT's

7
5

3

1
Description

2
Type

1
Order code

Qty needed
CT’s

6

2

Description

4

3

Type

Order codePT’s

2
Qty needed
CT’s

PT’s

1 Terminal block

ZS10-ST-T4

1SNK508311R0000 6

41 Terminal block

ZS10-ST-T4

1SNK508311R0000 3

0

2 End section

ES10-ST

1SNK508910R0000 1

1

2 Terminal block

ZS10-R1

1SNK508011R0000 31

3 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 3

0

3 Terminal block

ZS10-ST-1

1SNK508312R0000 0

3

4 End section

ES10-ST

1SNK508910R0000 1

1

5 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 30

6 Test socket

AL4-M3

1SNA206721R0100 0

1

7 Insulated test socket

AJS9

1SNA179726R0200 3

0

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160058S0201

8

SNK series, terminal blocks
Test & measurement - Typical schematic for measuring devices

Common point on the terminal block assembly
CT's

L1
P1

L2
L3

PT's
P1

P1
S1

P2 S1

P2 S1

P2
S2

S2

S2

P

P

P

S

S

S

1

2

3

N

N

Voltage inputs

Current inputs

Measuring devices(ie: meters, protection relays…)

Bill of material with convenient customization(test sockets, feed-through terminals…)

Bill of material optimized
4

CT's

9

PT's

CT's

PT's

8
5

8

6
7

Description

2 3
Type

Order code1
Qty needed
CT’s2

Description

4 5

3

Type

Order codePT’s

2
Qty needed
CT’s

PT’s

1 Terminal block

ZS10-ST-T4

1SNK508311R0000 6

41 Terminal block

ZS10-ST-T4

1SNK508311R0000 3

0

2 Terminal block

ZS10-PE-R1 1SNK508151R0000 1

0

2 Terminal block

ZS10-R1

1SNK508011R0000 3

1

3 End section

ES10-ST

1SNK508910R0000 1

1

3 Terminal block

ZS10-ST-1

1SNK508312R0000 0

3

4 Lateral jumper bars

PC8-R1

1SNA400711R0600 1

0

4 Terminal block

ZS10-PE-R1 1SNK508151R0000 1

0

5 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 3

0

5 End section

ES10-ST

1SNK508910R0000 1

1

6 Short-circuit bridges

SC-JB8-2

1SNK900652R0000 30

7 Test socket

AL4-M3

1SNA206721R0100 0

1

8 Insulated test socket

AJS9

1SNA179726R0200 30

9 Lateral jumper bars

PC8-R1

1SNA400711R0600 1

0PAGE 301

1SNK160058S0201

1

ZS10-ST screw clamp terminal blocks
Test disconnect with sliding link - 8 mm 0.315 in spacing
Description

10 mm²–– Secure your disconnect operations in control circuits with the robust sliding link operated with a screwdriver,–– Customize ZS10-ST with colored test sockets in order to identify conveniently each phase of the Current
Transformer or Potential Transformers secondary circuits,–– Fully compatible with the ZS10-ST-T4 accessories.

6 AWG

1SNK161065F0014

Ordering details
Description

Color

DisconnectGrey

61 2.40"

53.5 2.11"

80.7 3.18"

Part Number

ZS10-ST

1SNK508310R0000

Main technical data

Pkg

Weightqty(1 pce) g

25

24.80

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
50 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 VIP20

300 V

1 conductor
per clamp

ZS10-STType

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 12 AWG
53 A / 6 AWG

TorqueDisconnect device
Tool
TorqueNEMA 1

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
1.3 Nm ± 0.3
11.5 lb.in ± 2.65
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in

38.7 1.52"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

BV

EAC

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

4
5

Color

10 mm
0.394 in
2 mm
0.079 in
2 poles
50 A (IEC)3 poles
50 A (IEC)4 poles
50 A (IEC)
5 poles
50 A (IEC)
10 poles
50 A (IEC)
Circuit separators 3 mm
0.118 in
Test sockets
Test sockets DIA 4 mm 0.157 in
End stops
End sections
Jumper bars

Type

Dark grey
Dark grey
OrangeDark grey
Yellow
Black
Green
Grey
Blue
Red

8

White
PurpleBrown

6

Terminal block
markers

DIA 4 mm 0.157 in - H=12 mm 0.492 in - M3 screw
Blank marker
Blank card

White

Universal wire markers holder

GreyPart Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
JB8-2-R1
1SNK908902R0000
JB8-3-R1
1SNK908903R0000
JB8-4-R1
1SNK908904R0000
JB8-5-R1
1SNK908905R0000
JB8-10-R1
1SNK908910R0000
CS-R3
1SNK900107R0000
AJS9
1SNA179726R0200
AJS9-BK
1SNA206680R1500
AJS9-GN
1SNA206681R0200
AJS9-GR
1SNA206682R0300
AJS9-BL
1SNA206683R0400
AJS9-RD
1SNA206720R1400
AJS9-WH
1SNA206765R0000
AJS9-PR
1SNA206772R0000
AJS9-BR
1SNA206782R0000
AL4-M3
1SNA206721R0100
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
20
25
25
25
25
25
25
25
25
25
50
1680
22
20
10

14.00
3.5
7.6
11.6
15.5
19.4
39.00
6.40
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
1.10
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description

ZS10-R1

ZS10-PE-R1

Feed-throughGroundColor
Profile aligned with ZS10-ST...
Profile aligned with ZS10-ST...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreyGreen-yellow

Type
ZS10-R1
ZS10-PE-R1

Part Number
1SNK508011R0000
1SNK508151R0000

Pkg

Weightqty(1 pce) g

25
25

20.90
28.40

1SNK161056S0201

Screw clamp terminal blocks

ZS10-ST-1 screw clamp terminal blocks
Test disconnect with sliding link for Potential Transformer circuits - 8 mm 0.315 in spacing
Description

10 mm²

Test terminal blocks especially designed for Potential Transformers circuits:–– low profile voltage measurement thanks to the two compact built-in test sockets compatible with DIA 4 mm
0.157 in test plugs,–– Installed with our aligned feed-through and ground terminal blocks, you benefit of a complete and compact
solution for your PT circuits.
1SNK161069F0014

6 AWG

Ordering details
Description

Color

Type

With 2 test sockets DIA 4 mm
0.157 in

Disconnect

Grey

ZS10-ST-1

1SNK508312R0000

Main technical data
ZS10-ST-1

61 2.40"

53.5 2.11"

38.7 1.52"

8 mm 0.315 in spacing

Pkg

Weightqty(1 pce) g

25

27.00

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
50 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 VIP10

300 V

1 conductor
per clamp

80.7 3.18"

Part Number

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 12 AWG
53 A / 6 AWG

TorqueDisconnect device
Tool
TorqueNEMA 1

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
1.3 Nm ± 0.3
11.5 lb.in ± 2.65
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

4
5
6
7

7

Color

End stops
10 mm
0.394 inEnd sections
2 mm
0.079 in
Lateral jumper bars 10 poles
4/6 poles
4/8 poles
4/10 poles
3/4 poles
4/7 poles
2/3 poles
4/6 poles
4/8 poles
Circuit separators 3 mm
0.118 inProtecting cover kits
Protecting covers 1 m 39.4 in length
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark greyBlack

Dark grey
Dark grey
Transparent
White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
PC8-10
1SNA163313R2400
PC8-R1
1SNA400711R0600
PC8-R2
1SNA400712R0700
PC8-R3
1SNA400713R0000
PC8-R4
1SNA400724R0300
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
KCO
1SNK900624R0000
CO
1SNK900604R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
1
1
1680
22
20
10

14.00
3.5
14.00
6.60
7.80
9.00
4.50
6.60
6.60
6.60
7.80
6.40
47.80
300.00
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Screw clamp terminal blocks

ZS10-R1

ZS10-PE-R1

Feed-throughGroundColor
Profile aligned with ZS10-ST...
Profile aligned with ZS10-ST...

Grey
Green-yellow

Type
ZS10-R1
ZS10-PE-R1

Part Number
1SNK508011R0000
1SNK508151R0000

Pkg

Weightqty(1 pce) g

25
25

20.90
28.40

Technical data valid for copper conductors only.

PAGE 303

1SNK161062S0201

Description

ZS10-ST-T4 screw clamp terminal blocks
Test disconnect with sliding link for Current Transformer circuits - 8 mm 0.315 in spacing
Description

10 mm²

Test terminal blocks especially designed for Current Transformers circuits:–– easy and safe current measurement thanks to the two insulated built-in test sockets compatible with IP20
DIA 4 mm 0.157 in test plugs (per IEC60101-031),–– convenient short-circuit operations with the SC-JB insulated sliding bridges.

6 AWG

Ordering details
1SNK161066F0014

Description

Color
With two yellow test sockets DIA
4 mm 0.157 in

Disconnect

62.6 2.46"

70.1 2.76"

61 2.40"

53.5 2.11"

80.7 3.18"

Grey

Part Number

ZS10-ST-T4

1SNK508311R0000

Main technical data

Pkg

Weightqty(1 pce) g

25

31.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
50 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 VIP20

300 V

1 conductor
per clamp

ZS10-ST-T4

Type

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 12 AWG
53 A / 6 AWG

TorqueDisconnect device
Tool
TorqueNEMA 1
Test socket
Tool

38.7 1.52"

8 mm 0.315 in spacing

TorqueTH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverØ 3.5 mm
Ø 0.138 in
1.3 Nm ± 0.3
11.5 lb.in ± 2.65
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138
0.4 Nm ... 0.6 Nm
3.5 lb.in ... 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3

3

4

5

6

7

8

8

4
5
6
7
8

Color

End stops
10 mm
0.394 inEnd sections
2 mm
0.079 in
Lateral jumper bars 10 poles
4/6 poles
4/8 poles
4/10 poles
3/4 poles
4/7 poles
2/3 poles
4/6 poles
4/8 poles
Circuit separators 3 mm
0.118 inProtecting cover kits
Protecting covers 1 m 39.4 in length
Short circuit
2 polesbridges
3 poles
4 poles
Terminal block
Blank marker
markers
Blank card

Dark grey
Dark greyBlack

Dark grey
Dark grey
Transparent
Yellow

White

Universal wire markers holder

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
PC8-10
1SNA163313R2400
PC8-R1
1SNA400711R0600
PC8-R2
1SNA400712R0700
PC8-R3
1SNA400713R0000
PC8-R4
1SNA400724R0300
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
KCO
1SNK900624R0000
CO
1SNK900604R0000
SC-JB8-2
1SNK900652R0000
SC-JB8-3
1SNK900653R0000
SC-JB8-4
1SNK900654R0000
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
1
1
25
25
25
1680
22
20
10

14.00
3.5
14.00
6.60
7.80
9.00
4.50
6.60
6.60
6.60
7.80
6.40
47.80
300.00
2.00
3.4
4.7
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Description

ZS10-R1

ZS10-PE-R1

Feed-throughGroundColor
Profile aligned with ZS10-ST...
Profile aligned with ZS10-ST...

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSGreyGreen-yellow

Type
ZS10-R1
ZS10-PE-R1

Part Number
1SNK508011R0000
1SNK508151R0000

Pkg

Weightqty(1 pce) g

25
25

20.90
28.40

1SNK161057S0201

Screw clamp terminal blocks

ZS10-R1 screw clamp terminal blocks
Feed-through - 8 mm 0.315 in spacing
Description

10 mm²–– With the same profile as the ZS10-ST..., the feed-through ZS10-R1 allows you to fully implement the electrical drawing of your CT or PT circuits,–– Fully compatible with the ZS10-ST... accessories.

6 AWG

Ordering details
1SNK161068F0014

Description
Feed-throughColor
Profile aligned with ZS10-ST...

Grey

61 2.40"

53.5 2.11"

80.7 3.18"

Part Number

ZS10-R1

1SNK508011R0000

Main technical data

Pkg

Weightqty(1 pce) g

25

20.90

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid: Solid/Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²A5-B5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
57 A / 10 mm²1200 A

24 ... 6 AWG

Wire stripping
length630 V
8000 VIP20

300 V

1 conductor
per clamp

ZS10-R1Type

24 ... 8 AWG
24 ... 10 AWG
20 ... 12 AWG

TH 35-7.5,
TH 35-15
13 mm
0.512 inFlat screwdriverToolØ 3.5 mm
Ø 0.138 in

20 ... 12 AWG
62 A / 6 AWG

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

TorqueNEMA 138.7 1.52"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3
4

5

6

7

4

5
6
7

10 mm
0.394 in
2 mm
0.079 in
2 poles
50 A (IEC)3 poles
50 A (IEC)4 poles
50 A (IEC)
5 poles
50 A (IEC)
10 poles
50 A (IEC)
Lateral jumper bars 4/7 poles
2/3 poles
4/6 poles
4/8 poles
Circuit separators 3 mm
0.118 in
Test sockets
Test sockets DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeBlack

Dark grey
Yellow
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
JB8-2-R1
1SNK908902R0000
JB8-3-R1
1SNK908903R0000
JB8-4-R1
1SNK908904R0000
JB8-5-R1
1SNK908905R0000
JB8-10-R1
1SNK908910R0000
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
AJS9
1SNA179726R0200
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
25
1680
22
20
10

14.00
3.5
7.6
11.6
15.5
19.4
39.00
6.60
6.60
6.60
7.80
6.40
3.60
0.27
10.00
14.00
0.20

8

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161059S0201

3

Color

Technical data valid for copper conductors only.

PAGE 305

ZS10-PE-R1 screw clamp terminal blocks
Ground - 8 mm 0.315 in spacing
Description

10 mm²–– With the same profile as the ZS10-ST..., the ground ZS10-PE-R1 allows you to fully implement the electricaldrawing of your CT or PT circuits,–– Fully compatible with the ZS10-ST... accessories,–– Short-circuit performances above the requirements of IEC 60947-7-2 terminal block standard,–– Secured snap on or remove from the rail.
1SNK161067F0014

6 AWG

Ordering details
Description

Color
Profile aligned with ZS10-ST...

GroundType

Green-yellow

ZS10-PE-R1

IEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 6 mm²
A5-B5

24 ... 6 AWG

Wire stripping
lengthMain technical data
1 conductor
per clamp

61 2.40"

53.5 2.11"

83.7 3.29"

1SNK508151R0000

Pkg

Weightqty(1 pce) g

25

28.40

Mounting instructions

Connecting capacity

ZS10-PE-R1

Part Number

Rigid: Solid/Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferrule
Gauge

24 ... 8 AWG
24 ... 10 AWG

Flat screwdriver

Tool
Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG
1596 A

Protection

IP20

NEMA 1

TH 35-7.5,
TH 35-15
13 mm
0.512 inØ 3.5 mm
Ø 0.138 in

1.3 Nm ± 0.3
11.5 lb.in ± 2.65

Torque38.7 1.52"

8 mm 0.315 in spacing

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com
CE

CB

RoHS

USR CNR

CSA

EAC

BV

DNV

Accessories
1

Description

2
1
2
3
4

5

6

7

4

5
6
7

10 mm
0.394 in
2 mm
0.079 in
2 poles
50 A (IEC)3 poles
50 A (IEC)4 poles
50 A (IEC)
5 poles
50 A (IEC)
10 poles
50 A (IEC)
Lateral jumper bars 4/7 poles
2/3 poles
4/6 poles
4/8 poles
Circuit separators 3 mm
0.118 in
Test sockets
Test sockets DIA 4 mm 0.157 in
Terminal block
Blank marker
markers
Blank card
End stops
End sections
Jumper bars

Universal wire markers holder

Dark grey
Dark grey
OrangeBlack

Dark grey
Yellow
White

Grey

Type

Part Number

BAM4
1SNK900001R0000
ES10-ST
1SNK508910R0000
JB8-2-R1
1SNK908902R0000
JB8-3-R1
1SNK908903R0000
JB8-4-R1
1SNK908904R0000
JB8-5-R1
1SNK908905R0000
JB8-10-R1
1SNK908910R0000
PC8-R5
1SNA400842R0000
PC8-R6
1SNA400843R0000
PC8-R7
1SNA400849R0000
PC8-R8
1SNA400850R0000
CS-R3
1SNK900107R0000
AJS9
1SNA179726R0200
MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
20
25
1680
22
20
10

14.00
3.5
7.6
11.6
15.5
19.4
39.00
6.60
6.60
6.60
7.80
6.40
3.60
0.27
10.00
14.00
0.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNK161058S0201

8

3

Color

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSPB-125

8

PAGE 307

Summary_9

9INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSRailway applications, terminal blocks
Accessories

Common terminal block accessories				
Mounting railPR		

310-313

SNK series, common terminal block accessories				
Screw end stops

BAM4, BAZH1

314

Screwless end stops

BAZ1		

315

Label holders

LH, LH-R1

316

LH-J			

317

Screwless jumper bars

JB5		

318

JB6		

319

JB8

320

JB10

321

JB12		322
Cross spacing jumpers

JB85-3		

Test adapters

TP2, TP4		

323
324

Test connectors

TC5		

325

Component plugs

PG5-R2		

326

PG5, PG5-R1

327

Screwdrivers

TO 		

328

Crimping tools

PS		

328

PI-Spring terminal block accessories
End sections

EK		329-331

Circuit separators

CS-R2, CS-R3		332-333

Shield connectors

SHBP, SHB		334

Screw clamp terminal block accessories
End sections

ES		335-336

Screw jumper bars

JB8		

337

JB16, JB22

338		JB26			339

BJMI31, BJMI36

340

Lateral jumper bars

PC8, PC81		

341

Circuit separator

CS, CS-R1		

342

Shield connectors

SHBS, SHB

343

Protecting covers

PL		

344

CO, KCO345

Short circuit bridges

SC-JB8346

Test sockets

AJS9		

347

Pluggable terminal block accessories
End sections

EDK, EDS		

Coding pegs

COP		

348-349

Locking devices

VR		350

350

Summary_99PAGE 309

PR mounting rail
Common terminal block accessories

1SNK500072F0000

Description–– Pre-punched symmetrical mounting rail,–– The slotted holes ease the mounting and allow to use existing and/or numerous fixings,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

Prepunched rail

PR30

1SNA173220R0500

Weight(1 pce) g2

328.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data

PR30

Zinc plating and passivation steel
TH 35-7.5

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

Description

1SNK500073F0000–– Symmetrical mounting rail complying with IEC60715,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

PR3.Z2

1SNA174300R1700

2

Weight(1 pce) g

718.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR3.Z2

Material
Rail

Zinc plating and passivation steel
TH 35-7.5

Equivalent E-Cu cross section

IEC
16 mm²

UL - CSA

All the main technical data provided are "manufacturer" values.
RoHS

9

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).
1SNK160017S0201

2000 mm 78.74 in spacing

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSPR mounting rail
Common terminal block accessories
Description

1SNK500073F0000–– Symmetrical mounting rail made of galvanised steel, complying with IEC60715,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

PR3.G2

1SNA164800R0300

2

Weight(1 pce) g

718.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR3.G2

Material
Rail

Galvanised steel
TH 35-7.5

Equivalent E-Cu cross section

IEC
16 mm²

UL - CSA

All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

Description

1SNK500074F0000–– Pre-punched symmetrical mounting rail,–– The slotted holes ease the mounting and allow to use existing and/or numerous fixings.

Ordering details
Description

Color

Preprunched rail

Type
PR50

Part Number
1SNA178529R0400

Pkg

Weightmeter(1 pce) g

21288.00

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR50

Zinc plating and passivation steel
TH 35-15

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

9

Mounting instructions

1SNK160040S0201–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

2000 mm 78.74 in spacing

Technical data valid for copper conductors only.

PAGE 311

PR mounting rail
Common terminal block accessories
Description

1SNK500075F0000–– Symmetrical mounting rail.

Ordering details
Description

Color

Type
PR5

Part Number
1SNA168700R2200

Pkg

Weightmeter(1 pce) g

21200.00

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Zinc plating and passivation steel
TH 35-15

Material
Rail

PR5

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

2000 mm 78.74 in spacing

1SNK500076F0000

Description–– Symmetrical mounting rail complying with IEC60715,–– The rigidity of the rail is maximised by the 2.3 mm 0.090 in thickness of the rail, and by its solid, non slotted
construction,–– PR4 TH 35-15 is the most rigid mounting rail solution and it can suppo

Ordering details
Description

Color

Type

Part Number

Pkg
meter

Recommended for SNK ground terminal blocks up to
35 mm² 2 AWG
PR4

PR4

1SNA168500R1200

2

Weight(1 pce) g

915.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Material
Rail

Zinc plating and passivation steel
TH 35-15

Equivalent E-Cu cross section

IEC
50 mm²

UL - CSA
2 AWG

All the main technical data provided are "manufacturer" values.

9

RoHS

2000 mm 78.74 in spacing–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160041S0201

Mounting instructions

PR mounting rail
Common terminal block accessories
Description

1SNC160411F0014–– Symmetrical mounting rail type 2 reinforced,–– Particularly well adapted for railway applications.

Ordering details
Description

Color

Type
PRH2R

Part Numbers
1SNA163350R1500

Pkg

Weightpce(1 pce) g

2

278.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PRH2R

Aluminium alloy
Type 2

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it,–– To prevent the rail from flexing, fixing is recommended every 250 mm 9.84 in,–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail.

9

1SNC167083S0201 - Rev. A

2000 mm 78.74 in spacing

PAGE 313

Screw end stops
Common terminal block accessories

1SNK160333V0014

BAM4 screw end stops
Description–– Give efficient support to the SNK terminal blocks assemblies thanks to the BAM4 double gripping rail contact,–– Ease the assemblies identification with the BAM4 marking location compatible with all SNK markers and labels.

Ordering details
Description

BAM4

Color

10 mm 0.394 in spacing

53.6 2.11"

Type

Dark grey

BAM4

36.2 1.42"

43.7 1.72"

Main technical data
Material specifications
Ambient temperature
min/max
26.8 1.06"

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900001R0000

Pkg

Weightqty(1 pce) g

50

14.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueTH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.9 Nm ± 0.1
7.08 lb.in ± 0.88

10 mm 0.394 in spacing

Mounting instructions

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Terminal block markers
Blank cardcompatible with MG3
In polycarbonate
In polyamide
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

White

Dark grey
Grey

Type

Part Number

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
LH
1SNK900605R0000
LH-R1
1SNK900607R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

1680
22
20
50
50
10

0.27
10.00
14.00
0.60
1.10
0.20

BAZH1 screw end stops
1SNK160094F0014

Description–– Give efficient support to the SNK double deck or power terminal blocks assemblies thanks to the BAZH1
double gripping rail contact,–– Ease the assemblies identification with label holders.

Ordering details
Description
BAZH1

Color

10 mm 0.394 in spacing

74.4 2.93"

Type

Dark grey

BAZH1

73.2 2.88"

65.7 2.59"

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900102R0000

Weight(1 pce) g

20

24.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

TH 35-7.5
Flat screwdriverØ 5.5 mm
Ø 0.217 in

Torque1.3 Nm ± 0.1
11.4 lb.in ± 0.88

Part Number

Pkg

Weightqty(1 pce) g

1680
22
20
50
50
10

0.27
10.00
14.00
0.60
1.10
0.20

37.2 1.46"

10 mm 0.394 in spacing
All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Terminal block markers
Blank cardcompatible with MG3
In polycarbonate
In polyamide
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color
White

Dark grey
Grey

Type

MG-CPM 13 41791 1SNB041791R0612
MC812
1SNK160000R0000
MC812PA1SNK169999R0000
LH
1SNK900605R0000
LH-R1
1SNK900607R0000
UMH
1SNK900611R0000

1SNK160026S0201

9

Pkg
qty

Screwless end stops
Common terminal block accessories

BAZ1 screwless end stops
1SNK160247V0014

Description–– Reduce the size of your terminal block assemblies with the screwless reduced spacing BAZ1 end stop,–– Ease the assemblies identification with various markers and label holders.

Ordering details
Description

BAZ1

Color

5.2 mm 0.205 in spacing

53.5 2.11"

Type

Dark grey

BAZ1Main technical data
43.2 1.72"

35.7 1.43"

34.2 / 1.35"

Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900002R0000

Pkg

Weightqty(1 pce) g

50

5.30

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail

TH 35-7.5

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
50
50
10

0.23
9.00
10.00
0.60
1.10
0.20

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

24.2 0.95"

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Terminal block markers
Blank cardcompatible with MG3compatible with HTP500
compatible with AMS600
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

Color
White

Dark grey
Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
LH
1SNK900605R0000
LH-R1
1SNK900607R0000
UMH
1SNK900611R0000

9

1SNK160002S0201

5.2 mm 0.205 in spacing

Technical data valid for copper conductors only.

PAGE 315

Label holder
Common terminal block accessories

1SNK160334V0014

LH label holder
Description–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Ordering details
Description
LH

Color

10 mm 0.394 in width

10 mm 0.394 in spacing

Type

Dark grey

LHPart Number

Pkg

Weightqty(1 pce) g

1SNK900605R0000

50

0.60

Part Number

Pkg

Weightqty(1 pce) g

25
25
25
10
1650
825
825
25

10.00
9.80
12.10
4.00
0.371
0.55
0.55
10.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

White
Self-adhesive precut blank label compatible with HTP500
White
Self-adhesive precut blank compatible with HTP500
label
Yellow
Pre-printed cover marker
Protection for RCPEAD markers Transparent
White
Precut blank label
compatible with MG3
Yellow
Self-adhesive precut blank compatible with MG3
label
White
Yellow
Self-adhesive precut blank label compatible with HTP500

Type
MCLH
RCPEAD-TT
RCPEAD-TT-YL
EPR2
MG-TAR 45490
MG-TAA 49448
MG-TAA 49498
MCLH-YL

1SNK900630R0000
1SNA235158R0100
1SNA235159R0200
1SNA399726R0700
1SNB045490R8530
1SNB049448R8530
1SNB049498R8530
1SNK900633R0000

1SNK160335V0014

LH-R1 label holder
Description–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Ordering details
LH
19.5 mm 0.768 in spacing

Mounting instructions

Description

Color

19.5 mm 0.768 in widthType

Dark grey

LH-R1

Part Number

Pkg

Weightqty(1 pce) g

1SNK900607R0000

50

1.10

Part Number

Pkg

Weightqty(1 pce) g

25
1
1
25
25
900
450
450
25

10.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Self-adhesive precut blank label compatible with HTP500
Precut blank label
compatible with AMS600
Protection for RCPEB markers
Self-adhesive precut blank compatible with HTP500
label
Precut blank label
compatible with MG3
Self-adhesive precut blanklabel
Self-adhesive precut blank label compatible with HTP500
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color
White
White
Transparent
White
YellowWhite
YellowWhite
YellowType
MCLH-R1
RCPEB
EPR1
PIB2-TT
PIB2-TT-YL
MG-TAR 45194
MG-TAA 49148
MG-TAA 49198
MCLH-R1-YL

1SNK900631R0000
1SNA178430R0500
1SNA178431R2200
1SNA235155R2600
1SNA235157R2000
1SNB045194R1735
1SNB049148R1735
1SNB049198R1735
1SNK900634R0000

0.05
9.70
9.40
0.62
0.91
0.91
10.00

1SNK160023S0201

9

Label holder
Common terminal block accessories

1SNK160347V0014

LH-J label holder
Description
Easily identify your block with three standard 5.2 mm 0.205 in spacing SNK markers. It fits in the jumper
channel of the SNK terminal blocks.

LH

Ordering details

4.8 mm 0.189 in spacing

87 3.4"94.5 3.7"

Description

Color

Rotating label holder with three SNK markers housings- 4.8 mm 0.189 in spacing

Dark grey

LH-J

Part Number

Pkg

Weightqty(1 pce) g

1SNK900606R0000

100

0.73

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Blank marker
Blank cardcompatible with MG3compatible with HTP500
compatible with AMS600
Universal wire markers holder 5.2 mm 0.205 in spacing

Color
White
White
White
Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

9

1SNK160096S0201

44.9 1.73"

TypeTechnical data valid for copper conductors only.

PAGE 317

JB5 screwless jumper bars
Common terminal block accessories

1SNK160143F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
JB5
5.2 mm 0.205 in spacing

Color

5.2 mm 0.205 in spacing

2 poles
3 poles
4 poles
5 poles
10 poles
50 polesOrangeType

Pkg

Part Number

JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50

1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000

Weightqty(1 pce) g

50
50
50
50
30
10

1.30
2.00
2.70
3.50
7.10
36.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
32 A
1000 V
800 V
630 V
400 V
400 V

UL - CSA
30 A
600 V
300 V
300 V
150 V
150 V

8000 V
IP20

NEMA 1Ex e
Pleaseconsultus

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.

915 poles max. recommended for convenient mounting.
3 - Cut poles

5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
For all other applications, please consult us.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160027S0201

4 - Alternated poles

JB6 screwless jumper bars
Common terminal block accessories

1SNK160143F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
6 mm 0.236 in spacingColor

6 mm 0.236 in spacing

2 poles
3 poles
4 poles
5 poles
10 poles
50 polesOrangeType

Pkg

Part Number

JB6-2
JB6-3
JB6-4
JB6-5
JB6-10JB6-50

1SNK906302R0000
1SNK906303R0000
1SNK906304R0000
1SNK906305R0000
1SNK906310R0000
1SNK906350R0000

Weightqty(1 pce) g

50
50
50
50
20
10

1.30
2.10
2.90
3.60
7.40
38.10

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
41 A
1000 V
800 V
630 V
400 V
400 V

UL - CSA
30 A
600 V
300 V
300 V
150 V
150 V

8000 V
IP20

NEMA 1Ex e
Please consult
our dedicatedcertificates

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.

915 poles max. recommended for convenient mounting.
3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
For all other applications, please consult us.

Technical data valid for copper conductors only.

PAGE 319

1SNK160029S0201

JB6

JB8 screwless jumper bars
Common terminal block accessories

1SNK160146F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
JB8
8 mm 0.315 in spacingColor

8 mm 0.315 in spacing

2 poles
3 poles
4 poles
5 poles
10 polesOrangeType

Pkg

Part Number

JB8-2
JB8-3
JB8-4
JB8-5
JB8-10

1SNK908302R0000
1SNK908303R0000
1SNK908304R0000
1SNK908305R0000
1SNK908310R0000

Weightqty(1 pce) g

50
50
50
40
20

2.70
4.10
5.60
7.00
14.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
57 A
1000 V
800 V
630 V
630 V
630 V

UL - CSA
42 A
600 V
300 V
300 V
150 V
150 V

6000 V
IP20

NEMA 1

Ex e
693 V
440 V
440 V
352 V
352 V

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.

9

3 - Cut poles
4 - Alternated poles

For all other applications, please consult us.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160030S0201

5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.

JB10 screwless jumper bars
Common terminal block accessories

1SNK160146F0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
10 mm 0.394 in spacingColor

10 mm 0.394 in spacing

2 poles
3 poles
4 poles
5 poles
10 polesOrangeType

Pkg

Part Number

JB10-2
JB10-3
JB10-4
JB10-5
JB10-10

1SNK910302R0000
1SNK910303R0000
1SNK910304R0000
1SNK910305R0000
1SNK910310R0000

Weightqty(1 pce) g

50
50
40
30
20

4.60
7.10
9.40
12.00
24.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
76 A
1000 V
800 V
630 V
400 V
250 V

UL - CSA
67 A
600 V
300 V
300 V
150 V
150 V

6000 V
IP20

NEMA 1

Ex e
693 V
440 V
440 V
275 V
176 V

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.

9

3 - Cut poles
4 - Alternated poles
5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.
1SNK160031S0201

JB10

For all other applications, please consult us.

Technical data valid for copper conductors only.

PAGE 321

JB12 screwless jumper bars
Common terminal block accessories

1SNK160239V0014

Description
Facilitate & secure your jumper bar assembly process:–– Screwless mounting,–– Pre-cut poles for alternated jumpering between terminal blocks,–– Insulated,–– Positive locking,–– Perfectly adapted to low level electrical contact (20mA, 50mV).

Ordering details
Description
JB12
12 mm 0.472 in spacingColor

12 mm 0.472 in spacing

2 poles
3 poles
5 polesOrangeType

Pkg

Part Number

JB12-2
JB12-3
JB12-5

1SNK912302R0000
1SNK912303R0000
1SNK912305R0000

Weightqty(1 pce) g

50
50
20

4.90
7.60
12.90

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage

1 - Standard use
2 - Cut extremities
3 - Cut poles
4 - Alternated poles
5 - Alternated poles
with cut extremities
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
76 A
1000 V
800 V
630 V
320 V
250 V

UL - CSA
67 A
600 V
300 V
300 V
150 V
150 V

6000 V
IP20

NEMA 1

Ex e
693 V
440 V
440 V
220 V
176 V

All the main technical data are indicative “manufacturer” values.
RoHS

Mounting instructions
1 - Standard use
2 - Cut extremities
For voltage rating > 50 V and Uimp > 2.5 KV, the below
accessories must be installed on the cut side of the jumper
to guarantee IP20 and voltage rating:

ZS...
ZK…

Feed-throughDouble deck / triple deck
All functions

CS circuit separator
ES… end section
EK… end section

Ensure a good straight cut by positioning the cutting tool on
the vertical snicks of the insulated part of the jumper.

9

3 - Cut poles
4 - Alternated poles

For all other applications, please consult us.

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

1SNK160071S0201

5 - Alternated poles with cut extremities
When using cut jumpers, cut extremities should be placed
oppositely to allow end sections / circuit separators placement at each cut extremities.

JB85-3 cross spacing jumpers
Common terminal block accessories

1SNK160125F0014

Description–– Allows power distribution between terminal blocks with different spacing,–– JB5-3, JB6-3 and JB8-3 can be used as cross spacing jumpers (see selection table on mounting instructions below).

Ordering details
Description

Color

Cross spacing jumpers

3 polesType

OrangePart Number

JB85-3

1SNK900603R0000

Pkg

Weightqty(1 pce) g

10

2.80

Main technical data
JB85

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Material specifications

8 mm 0.315 in spacing

Ambient temperature
min/max

Rated current
Rated voltage

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
32 A
1000 V
800 V
630 V
8000 V
IP20

Standard use
Cut extremities
Cut poles

Impulse withstand voltage
Protection-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA
30 A
600 V
300 V
300 V

Ex e
Please consult
our dedicatedcertificates

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

Mounting instructions
Cross spacing jumper selection between A and B terminal blocks with different
spacing.

B 5.2 mm

6 mm

8 mm

JB85.3
JB85.3
JB6.3

JB8.3
-

A
6 mm
8 mm
10 mm
12 mm

JB5.3
JB85.3
JB85.3
JB85.3I1 max

I max

I2 maxYellow cell: for ZS and ZK terminal blocks
Blue cell: for ZS terminal blocks only

I1 max + I2 max ≤ I max		
		
I max		I1 max≤ I rated terminal blockI2 max		

1SNK160054S0201

9

Technical data valid for copper conductors only.

PAGE 323

Test adapters
Common terminal block accessories

TP2 test adapters
1SNK160093V0014

Description–– Insulated test adapter that enables individual voltage control,–– Direct plug-in solution into the jumpers channels,–– Compatible with standard isolated or non isolated test plugs DIA 2 mm 0.079 in and 2.3 mm 0.090 in,–– Withstand more than 10000 operations according to TE Connectivity test standards.

Ordering details

TP

Description

7.6 mm 0.299 in spacing

Color

For test plugs DIA 2 mm 0.079 inMounting instructions

TP2

Part Number
1SNK900203R0000

Pkg

Weightqty(1 pce) g

20

1.70

Main technical data
Material specifications
Ambient temperature
min/max✔

Dark grey

Type

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Standard use
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
10 A
1000 V
8000 VIP20-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA

Ex e

600 V

Not authorized

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

TP4 test adapters
1SNK160093V0014

Description–– Isolated test adapter that enables individual voltage control,–– Direct plug-in solution into the jumpers channels,–– Compatible with standard insulated or non isolated test plugs DIA 4 mm 0.157 in,–– Withstand more than 10000 operations according to TE Connectivity test standards.

Ordering details

TP

Description

7.6 mm 0.299 in spacing

Color

For test plugs DIA 4 mm 0.157 inMounting instructions

Ambient temperature
min/max✔

TP4

Part Number
1SNK900205R0000

Pkg

Weightqty(1 pce) g

20

2.40

Main technical data
Material specifications

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Standard use
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
16 A
1000 V
8000 VIP20-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA

Ex e

600 V

Not authorized

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

1SNK160036S0201

9

Dark grey

TypeTechnical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSTC5 test connectors
Common terminal block accessories
Description
Ease the testing of terminal block assemblies:–– Make your own test connector assembly with our modular solution mixing various spacings,–– Direct plug-in solution into the jumpers channels,–– Withstand more than 10000 operations according to TE Connectivity test standards.
ES-TC6

ES-TC8Main technical data
IEC

Rigid - Solid / Stranded
Flexible without ferrule
Flexible with non insulated ferrule
Flexible with insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible without ferrule
per clamp
Flexible with twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 1.5 mm²0.22 ... 1.5 mm²

1 conductor
per clamp

TC5-R1TC5

5.2 mm 0.205 in spacing

TC5-R1
TC5

Mounting instructions

Connecting capacity

UL - CSA

0.22 ... 1.5 mm²A1-B1
0.2 ... 0.75 mm²0.22 ... 0.75 mm²0.22 ... 0.75 mm²
16 A / 1.5 mm²
180 A1000 V
8000 V
IP20

RailWire stripping
lengthTool

Torque8 mm
0.314 inFlat screwdriverØ 2.5 mm
Ø 0.098 in

0.5 Nm ± 0.1
3.43 lb.in ± 0.885

NEMA 1

The connecting capacity data for one Rigid - Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

Material specifications
Ambient temperature
min/max
10 poles max.

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

TC5-R1

Ordering details

ES-TC6

Test connectors for 5.2 mm 0.205 in spacing terminal blocks
Description

Color

Test connectors 5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 in

Dark grey

Part Number

TC5
TC5-R1

1SNK900200R0000
1SNK900201R0000

TypePart Number

Pkg

Weightqty(1 pce) g

10
10

5.20
5.20

Ordering details

10 poles max.

Test connectors for 6 mm 0.236 in spacing terminal blocks
Description

TC5-R1

TypeTC5ES-TC8Color

Test connectors End module, 5.2 mm 0.205 inSpacers
0.8 mm 0.031 in spacing

Dark grey

TC5-R1
ES-TC6

1SNK900201R0000
1SNK900105R0000

TypePart Number

Pkg

Weightqty(1 pce) g

10
10

5.20
0.80

Ordering details
Test connectors for 8 mm 0.315 in spacing terminal blocks
Description

10 poles max.

Color

Test connectors 5.2 mm 0.205 in spacing
End module, 5.2 mm 0.205 inSpacers
2.8 mm 0.110 in spacing

Pkg

Weightqty(1 pce) g

5.20
5.20
1.40

Dark grey

TC5
TC5-R1
ES-TC8

1SNK900200R0000
1SNK900201R0000
1SNK900104R0000

10
10
10

Color

Type

Part Number

Pkg

Weightqty(1 pce) g

20
1960
22
20
10

1.00
0.23
9.00
10.00
0.20

9

Description

PT-3

Cable clamps
Terminal block
markers

Fit on two C2.5-ZDP plugs and on TC5 test connectors
Blank marker
Blank card
Universal wire markers holder

Dark grey
White

Grey

PT-3
1SNK900625R0000
MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Technical data valid for copper conductors only.

PAGE 325

1SNK160042S0201

Accessories

Component plugs
Common terminal block accessories

PG5-R2 component plugs
Description
48.9 1.92"

27.8 1.09"

1SNK160112F0014

37.7 1.48"

18.9 .74"–– Component holder compatible with 5.2 mm 0.205 in spacing ZS4 feed-through terminal blocks,–– Fit components 16 x 16 x 8.5 mm 0.630 x 0.630 x 0.335 in (not supplied with plug) such as resistors, diodes, varistance,–– Direct plug-in into the terminal blocks jumper channels,–– Maximum dissipatived power: 2 W.

PG5
9.95 mm 0.392 in spacing

Ordering details
Description

Mounting instructions

Color

Components insertion between 2 blocks

Type

Dark grey

PG5-R2

Part Number

Pkg

Weightqty(1 pce) g

1SNK900403R0000

20

8.00

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Impulse withstand voltage
Protection

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC

UL - CSA

250 V
4000 V
IP20

NEMA 1

All the main technical data provided are "manufacturer" values–– Open the PG5-R2 with a flat screw-

driver DIA . 3.5 mm 0.138 in,–– Use a soldering iron to fix your component,–– Close the PG5-R2,–– Plug-in in the terminal blocks jumper
channels.

RoHS

Accessories
Description
Terminal block markers
Blank card
Universal wire markers holder

Color
White

In polycarbonate
Blank card
5.2 mm 0.205 in spacing

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

1SNK160039S0201

9

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSComponent plugs
Common terminal block accessories

PG5 component plugs
Description
39 1.54"24.6 .97"

1SNK160022F0014

31 1.22"

17 .67"–– Ease the components installation ( components not supplied with plug ) with our quick plug-in mounting
system which avoids soldering process,–– Accept 8.8 x 3.2 mm 0.346 x 0.125 in components such as resistors, diodes or subminiature fuses (fully
encapsulated),–– Maximum dissipatived power: 1 W.

PG5Ordering details

5.2 mm 0.205 in spacing

Description

Color

Components in series with circuit

Mounting instructions

Type

Dark grey

PG5

Part Number

Pkg

Weightqty(1 pce) g

1SNK900401R0000

20

3.50

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Rated current
Rated voltage
Impulse withstand voltage
Protection–– Direct plug-in in disconnect withplug terminal block

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC

UL - CSA

400 V
6000 V
IP20

150 V
NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Terminal block markers
Blank card

White

In polycarbonate
Blank card
5.2 mm 0.205 in spacing

Universal wire markers holder

Description
39 1.54"24.6 .97"

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

PG5-R1 disconnect plugs

31 1.22"

1SNK160120F0014

Grey

Type

Allow disconnect function when associated with the disconnect with plug terminal blocks.

Ordering details
Description

Color

Type

Part Number

17 .67"Equipped with linking bar

OrangePG5Main technical data

5.2 mm 0.205 in spacing

Material specifications

Mounting instructions

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C
IEC
18 A
400 V
6000 V
IP20

Rated current
Rated voltage
Impulse withstand voltage
Protection

PG5-R1

1SNK900402R0000

Pkg

Weightqty(1 pce) g

20

3.50

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F
UL - CSA
20 A
150 V

9

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS–– PG5-R1 totally inserted: closed circuit,–– PG5-R1 inserted in central position:
open circuit, plug secured in isolated
central position

Description
Terminal block markers
Blank card
Universal wire markers holder

Color
White

In polycarbonate
Blank card
5.2 mm 0.205 in spacing

Grey

Type

Part Number

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

Technical data valid for copper conductors only.

PAGE 327

1SNK160037S0201

Accessories

ToolsCommon terminal block accessories

TO screwdrivers
1SNK160242F0014

Description

Ordering details
Description

Color

Insulated screwdriver 1000V IEC dimensions 3.5 x
100 mm 0.138 x 3.94 inscrewdriver 3.5 x 50 mm 0.138 x 1.97 inscrewdriver 3.5 x 50 mm 0.138 x 1.97 in Angled 60°
screwdriver 4 x 100 mm 0.157 x 3.94 inscrewdriver 5.5 x 125 mm 0.216 x 4.92 inscrewdriver 6.5 x 150 mm 0.256 x 5.90 in

1SNK160127F0014

TO

PS

Flat head screwdriver

Type

Part Number

Pkg

Weightqty(1 pce) g

TO3.5-100-INS

1SNK900644R0000

1

37.00

TO3.5-50
TO3.5-50-A
TO4-100
TO5.5-125
TO6.5-150

1SNK900640R0000
1SNK900659R0000
1SNK900641R0000
1SNK900642R0000
1SNK900643R0000

12
12
1
1
1

22.00
21.6
42.00
75.50
121.00PS crimping tools
Description–– Crimp flexible conductors equipped with ferrules from 0.08 to 10 mm² 28 AWG to 7 AWG,–– Semi-automatic crimping tool.

Ordering details
Description
180 mm 7.09 in length

Color

Type
PS-3

Part Number
1SNK900650R0000

Pkg

Weightqty(1 pce) g1

380.00

1SNK160028S0201

9

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSEnd sections
PI-Spring terminal block accessories

EK2.5 end sections
1SNK160233V0014

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5, ZK2.5-PE, ZK4, ZK4-PE, ZK6 and ZK6-PE PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

EK2.5

Dark grey

Type
EK2.5

Part Number
1SNK705910R0000

Pkg

Weightqty(1 pce) g

20

1.80

1SNK160234V0014

EK2.5-3P end sections
Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5-3P, ZK2.5-PE-3P, ZK4-3P, ZK4-PE-3P, ZK2.5-S..., ZK2.5-SP and ZK2.5-SF... PISpring screwless terminal blocks.

Ordering details
EK2.5-3P

Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-3PPart Number
1SNK705911R0000

Pkg

Weightqty(1 pce) g

20

2.40

EK2.5-4P

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5-4P, ZK2.5-PE-4P, ZK4-4P and ZK4-PE-4P PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-4P

Part Number
1SNK705912R0000

Pkg

Weightqty(1 pce) g

20

2.70

9

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160064S0201

1SNK160235V0014

EK2.5-4P end sections

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 329

End sections
PI-Spring terminal block accessories

1SNK160339V0014

EK2.5-S-4P end sections
Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK2.5-S-4P, ZK2.5-SP-4P, ZK2.5-CH-4P... PI-Spring screwless terminal blocks.

Ordering details

EK2.5-S-4P

Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-S-4PPart Number
1SNK705913R0000

Pkg

Weightqty(1 pce) g

20

2.94

EK2.5-D2 end sections
1SNK160237V0014

Description–– Compatible with ZK2.5-D2, ZK2.5-D2-PE, ZK2.5-D1 and ZK2.5-D1-PE PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK2.5-D2

Part Number
1SNK705960R0000

Pkg

Weightqty(1 pce) g

20

3.40

EK2.5-D2

EK2.5-T3 end sections
1SNK160346V0014

Description–– Compatible with ZK2.5-T3, ZK2.5-T1, ZK2.5-T1-PE, ZK2.5-L-L-PE and ZK2.5-L-N-PE PI-Spring screwless
terminal blocks.

Ordering details
Description

Color

0.8 mm 0.031 in spacing

Dark grey

Type
EK2.5-T3

Part Number
1SNK705961R0000

Pkg

Weightqty(1 pce) g

20

4.76

EK2.5-T3

9

Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160065S0201

Main technical data

End sections
PI-Spring terminal block accessories

1SNK160236V0014

EK6-3P end sections
Description–– Compatible with ZK6-3P and ZK6-PE-3P PI-Spring screwless terminal blocks.

Ordering details
Description

EK6-3PColor

2 mm 0.079 in spacing

Dark grey

Type
EK6-3PPart Number
1SNK708911R0000

Pkg

Weightqty(1 pce) g

20

2.80

1SNK160238V0014

EK10 end sections
Description–– Compatible with ZK10, ZK10-PE, ZK16 and ZK16-PE PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK10

Part Number
1SNK710910R0000

Pkg

Weightqty(1 pce) g

20

3.30

EK10

1SNK160318V0014

EK10-3P end sections
Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with ZK10-3P, ZK10-PE-3P, ZK16-3P, ZK16-PE-3P... PI-Spring screwless terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

Dark grey

Type
EK10-3P

Part Number
1SNK710911R0000

Pkg

Weightqty(1 pce) g

20

4.5

9

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160095S0201

EK10-3P

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 331

Circuit separators
PI-Spring terminal blocks accessories

CS-R2 circuit separators
1SNK160240V0014

Description–– Compact circuits separator solution (only 3mm spacing) which provides a convenient visual identification of
the several circuits within terminal assemblies,–– Unique top marking possibility that can replace the conventional solution of "end stop with label holder"for demanding applications with high space constraints, - Compatible with all PI-spring feed-through andground terminal blocks up to 8 mm spacing,–– Mounting on DIN3-TH35 rail.

Ordering details
Description

CS-R2
61.8 2.67"

Color

3 mm 0.118 in spacing

Type

Dark grey

CS-R2

Part Number

Pkg

Weightqty(1 pce) g

1SNK900106R0000

20

3.80

Part Number

Pkg

Weightqty(1 pce) g

1680
5250
5250
22
20
10

0.27
0.04
0.05
10.00
11.00
0.20

48.7 1.92"

Main technical data
Material specifications
Ambient temperature
min/max

3 mm 0.118 in spacing

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Terminal block markers
LabelsColor
White
Yellow
White

Blank card

In polycarbonate
Blank card
Universal wire markers holder 5.2 mm 0.205 in spacing

White
Grey

Type

MG-CPM 13 41791 1SNB041791R0612
MG-VYT 46415
1SNB046415R0615
MG-VYT 46915
1SNB046915R0615
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

1SNK160072S0201

9

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSCircuit separators
PI-Spring terminal blocks accessories

1SNK160241V0014

CS-R3 circuit separators

CS-R3
98.8 3.89"

Description–– Compact circuits separator solution (only 3mm spacing) which provides a convenient visual identification of
the several circuits within terminal assemblies,–– Unique top marking possibility that can replace the conventional solution of "end stop with label holder" fordemanding applications with high space constraints,–– Compatible with all single deck PI-spring terminal blocks and ZS10-ST...terminal blocks ,–– Mounting on DIN3-TH35 rail.

Ordering details

3 mm 0.118 in spacingColor

3 mm 0.118 in spacing

Type

Dark grey

CS-R3

Part Number

Pkg

Weightqty(1 pce) g

1SNK900107R0000

20

6.40

Part Number

Pkg

Weightqty(1 pce) g

1960
1680
5250
5250
22
20
22
20
10

0.23
0.27
0.04
0.05
9.00
10.00
10.00
11.00
0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Terminal block markers

White

LabelsYellow
White

Blank card

In polycarbonate
Blank card
In polycarbonate
Blank card
Universal wire markers holder 5.2 mm 0.205 in spacing

White

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MG-CPM 13 41791 1SNB041791R0612
MG-VYT 46415
1SNB046415R0615
MG-VYT 46915
1SNB046915R0615
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
MC612
1SNK150000R0000
MC612PA1SNK159999R0000
UMH
1SNK900611R0000

9

1SNK160098S0201

53.7 2.11"

Description

Technical data valid for copper conductors only.

PAGE 333

1SNK160267F0014

Shield connectors
PI-Spring terminal block accessories

SHBP/SHBSHBP/SHB shield connectors for PI-Spring terminal blocks
Description–– Ensure the continuity of your shield connection,–– Various connection solutions available: RILS cable ties, soldering, quick-connect.

Ordering details
13.67 .54"

Description
128 5.04"
SHB

Color

Compatible with ZK2.5 and ZK2.5-S terminal blocks
Compatible with ZS and ZK double deck terminal blocks

Type
SHBP
SHB

Part Number
1SNK900601R0000
1SNK900602R0000

Pkg

Weightqty(1 pce) g

20
20

4.10
4.90

SHBP

12.2 0.48"

Main technical data
Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Material specifications
Ambient temperature
min/max

116 4.57"

SHBP
Rated voltage-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
100 V

UL - CSA

Ex e
50 V

All the main technical data provided are "manufacturer" values
RoHS

Accessories for screw clamp and PI-Spring terminal blocks
Description
Cable ties

Color
For SNK shield connector

Type
RILS

Part Number
1SNK900627R0000

Pkg

Weightqty(1 pce) g

10

0.30

Mounting instructions–– SHBS is directly fixed on the terminal block,–– SHB is fixed on the ES4-D2 end section,–– SHBP is directly fixed on the terminal block,–– Connect the cable shielding on the shielding connector with:–– RILS cable ties,–– quick-connect (the shield connector needs to beprepared),–– soldering iron.

1SNK160044S0201

9

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSEnd sections
Screw clamp terminal block accessories

ES4 end sections
1SNK161013F0014

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with feed-through, ground and disconnect screw clamp terminal blocks.

Ordering details
Description

Color

2.2 mm 0.087 in spacing

Dark grey

Type
ES4

Part Number
1SNK505910R0000

Pkg

Weightqty(1 pce) g

20

2.20

ES4

ES6-3S end sections
1SNK160229V0014

Description–– Compatible with ZS6-3S and ZS6-3S-PE terminal blocks.

Ordering details
Description

Color

2.2 mm 0.087 in spacing

Dark greyTypeES6-3SPart Number
1SNK505912R0000

Pkg

Weightqty(1 pce) g

20

2.50

ES6-3S

1SNK160230V0014

ES6-4S end sections
Description–– Compatible with ZS6-4S, ZS6-4S-PE, ZS6-S-4S-T2 and ZS4-PE-R2 terminal blocks.

Ordering details
Description

Color

2.2 mm 0.087 in spacing

ES6-4S

Dark greyTypeES6-4SPart Number
1SNK505911R0000

Pkg

Weightqty(1 pce) g

20

3.10

ES4-D2 end sections
1SNK161012F0014

Description–– Unique dark grey color that fits all terminal blocks colours and ease the identification of circuits within yourterminal block assemblies,–– Compatible with double deck screw clamp terminal blocks

Ordering details
Description

Color

2.55 mm 0.100 in spacing

Dark grey

Type
ES4-D2

Part Number
1SNK505960R0000

Pkg

Weightqty(1 pce) g

20

4.10
9

ES4-D2Main technical data

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160061S0201

Material specifications

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

PAGE 335

End sections
Screw clamp terminal block accessories

ES4-T3 end sections
Description
1SNK160232V0014–– Compatible with ZS4-T3 terminal block.

Ordering details
Description

Color

0.8 mm 0.031 in spacing

Type

Dark grey

ES4-T3

Part Number
1SNK505961R0000

Pkg

Weightqty(1 pce) g

20

4.20

ES4-T3

ES4-SF end sections
1SNK161026F0014

Description–– Compatible with fuse ZS4-SF1... and disconnect screw clamp terminal blocks ZS4-S-R3.

Ordering details
Description

Color

1.5 mm 0.059 in spacing

Type

Dark grey

Part Number

ES4-SF

1SNK508960R0000

TypePart Number

Pkg

Weightqty(1 pce) g

20

1.80

ES4-SF

ES4-D2-SF1 end sections
Description
1SNK160231V0014–– Compatible with ZS4-D2-SF1 ... terminal blocks.

Ordering details
Description

Color

2.5 mm 0.098 in spacing

Dark grey

ES4-D2-SF1

1SNK508911R0000

Pkg

Weightqty(1 pce) g

20

5.00

ES4-D2-SF1

1SNK161072F0014

ES10-ST end sections
Description–– Unique dark grey color that fits all test disconnect terminal blocks ZS10-ST... and ease the identification of
circuits within your terminal block assemblies,–– Also compatible with ZS10-R1 and ZS10-PE-R1.

Ordering details
Description
ES10-ST

Color

2 mm 0.079 in spacing

TypePart Number

Pkg

Weightqty(1 pce) g

3.5

Dark grey

ES10-ST

1SNK508910R0000

20

Color

Type

Part Number

Pkg

Weightqty(1 pce) g

20

0.20

Accessories
Description
Circuit separators

0 mm 0 in spacing

Dark greyCS

1SNK900101R0000

Main technical data
Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

1SNK160062S0201

9

Screw jumper bars
Screw clamp terminal block accessories

JB8 jumper bars
Description
1SNK160212F0014

Insulated jumper bar with screw mounting.

Ordering details
Description

Color

8 mm 0.315 in spacing

JB8
8 mm 0.315 in spacing

Orange

JB8-2-R1
JB8-3-R1
JB8-4-R1
JB8-5-R1
JB8-10-R1

Part Number
1SNK908902R0000
1SNK908903R0000
1SNK908904R0000
1SNK908905R0000
1SNK908910R0000

Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Standard use

IEC
50 A
160 V

a

Rated current
Rated voltage
b

10
10
10
10
10

7.6
11.6
15.5
19.4
39.00

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueUL - CSA
51 A

Alternated poles
Impulse withstand voltage
Protection

Flat screwdriverØ 3.5 mm
Ø 0.138 in

0.7 Nm ± 0.1
6.2 lb.in ± 0.88

Ex e

Not authorized
IP20

NEMA 1

All the main technical data provided are "manufacturer" values
RoHS

9

1SNK161061S0201

1 - Rated voltage: 160 V (IEC) / Not
authorized (UL)
2 - Rated voltage: 320 V (IEC) / Not
authorized (UL)
3 - Rated voltage: 1000 V (IEC) / 300
V (UL)
a - End section ES10-ST
b - End stop BAZ1

Weight(1 pce) g

Rail

2

3

Pkg
qty

Main technical data

Mounting instructions
1

2 poles
3 poles
4 poles
5 poles
10 poles

Type

Technical data valid for copper conductors only.

PAGE 337

Screw jumper bars
Screw clamp terminal block accessories

JB16 jumper bars
Description
1SNK160124F0014

Insulated jumper bar with screw mounting.

Ordering details
Description

Color

16 mm 0.630 in spacing

JB16
16 mm 0.630 in spacing

2 poles
3 poles
4 poles
5 poles
10 polesOrangeType
JB16-2
JB16-3
JB16-4
JB16-5
JB16-10

Part Number
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK916310R0000

Pkg

Weightqty(1 pce) g

10
10
10
10
10

10.00
16.00
22.00
28.00
56.60

Main technical data
Material specifications

Mounting instructions
Ambient temperature
min/max

Rated current
Rated voltage–– With flat pliers, cut out the partitions

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
125 A
1000 VUL - CSA
150 A
600 V

Rail

Alternated poles
Impulse withstand voltage
Protection

Tool
TorqueFlat screwdriverØ 5.5 mm
Ø 0.217 in

1.2 Nm ± 0.1
10.6 lb.in ± 0.885

Ex e

Not authorized
8000 V
IP20

NEMA 1

Color

Type

All the main technical data provided are "manufacturer" values
RoHS

Description
Screw jumper bars

Ordering details
Description

JB22

22 mm 0.866 in spacing

22 mm 0.866 in spacing

Mounting instructions

2 poles
3 poles
5 poles
10 polesJB22-2
JB22-3
JB22-5
JB22-10

Part Number
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK922310R0000

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide

5
5
5
5

27.00
43.30
76.10
157.40-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
192 A
1000 VUL - CSA
175 A
600 V

Rail
Tool
Torque9on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

Weight(1 pce) g

Main technical data
Material specifications–– With flat pliers, cut out the partitions

Pkg
qty

Rated current
Rated voltage

Alternated poles
Impulse withstand voltage
Protection
All the main technical data provided are "manufacturer" values
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSAllen keyØ 4 mmØ 0.157 in

2 Nm ± 0.4
17.7 lb.in ± 3.54

Ex e
630 V
Not authorized

8000 VIP20

1SNK160032S0201

1SNK160100F0014

JB22 jumper bars

Screw jumper bars
Screw clamp terminal block accessories

1SNK160100F0014

JB26 jumper bars
Description
Screw jumper bars

Ordering details
Description

JB26

Color

26 mm 1.02 in spacing

26 mm 1.024 in spacing

Mounting instructions

Ambient temperature
min/max

1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK926310R0000

Pkg

Weightqty(1 pce) g

5
5
5
5

41.20
65.70
115.70241.50

Rated current
Rated voltage

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
232 A
1000 VUL - CSA
230 A
600 V

Rail

Alternated poles
Impulse withstand voltage
Protection

Tool
TorqueAllen keyØ 4 mmØ 0.157 in

2 Nm ± 0.4
17.7 lb.in ± 3.54

Ex e
630 V
Not authorized

8000 V
IP20

All the main technical data provided are "manufacturer" values
RoHS

9

1SNK160034S0201

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

JB26-2
JB26-3
JB26-5
JB26-10

Part Number

Main technical data
Material specifications–– With flat pliers, cut out the partitions

2 poles
3 poles
5 poles
10 poles

Type

Technical data valid for copper conductors only.

PAGE 339

Screw jumper bars
Screw clamp terminal block accessories

1SNK160100F0014

BJMI31 jumper bars
Description
Screw jumper bars

Ordering details
Description

Color

31mm 1.220 in spacing

BJMI3131 mm 1.22 in spacing

2 poles
3 polesType
BJMI31.2
BJMI31.3

Part Number
1SNA206053R0700
1SNA206054R0000

Pkg

Weightqty(1 pce) g

1
1120.00190.00Main technical data
Material specifications

Mounting instructions

Ambient temperature
min/max

Rated current
Rated voltage–– With flat pliers, cut out the partitions

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
309 A
1000 VUL - CSA
445 A
600 V

Rail

Alternated poles

Tool
TorqueAllen keyØ 5 mmØ 0.196 in

3 Nm ± 0.4
26.55 lb.in ± 3.54

Ex e

Not authorized
8000 V
IP20

Impulse withstand voltage
Protection
All the main technical data provided are "manufacturer" values
RoHS

Description
Screw jumper bars

Ordering details
Description

BJMI3636 mm 1.42 in spacing

Mounting instructions

Color

36mm 1.41i7 n spacing

2 poles
3 polesMaterial specifications

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Standard use

IEC
415 A
1000 VUL - CSA
620 A
600 V

9

Rated current
Rated voltage

on the terminal block insulating body.
Be careful to not cut out the jumpered
terminal blocks partitions at both endsof the assembly in order to maintain theIP20, Nema1 protection and insulation,–– Install the jumper bar with the recommended tool and torque.

BJMI36.2
BJMI36.3

Part Number
1SNA206126R2500
1SNA206223R0600

Pkg

Weightqty(1 pce) g1
1

170.00260.00Main technical data

Ambient temperature
min/max–– With flat pliers, cut out the partitions

Type

Rail

Alternated poles
Impulse withstand voltage
Protection
All the main technical data provided are "manufacturer" values
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

ToolTorqueAllen keyØ 5 mmØ 0.196 in

3 Nm ± 0.4
26.55 lb.in ± 3.54

Ex e

Not authorized
8000 VIP20
1SNK160097S0201

1SNK160100F0014

BJMI36 jumper bars

1SNC160112F0014

Lateral jumper bars
Screw clamp terminal block accessories

PC8
8 mm 0.315 in spacing

PC8 lateral jumper bars
Description
IP20 Comb jumper bars,–– direct insertion in the screw clamp before tightening the screws, above the eventual conductor (if conductorused with ferrule, we recommend the use of long ferrule for optimized mounting ergonomy with test disconnect terminal blocks),–– Multiple versions available in pre-cut poles for test disconnect terminal blocks applications.

Ordering details

Mounting instructions for
ZS10-ST...

Description

Color

Lateral jumper bars
8 mm 0.315 in 2 poles
spacing
3 poles
4 poles
10 poles1a2b

1 - Rated voltage: 630 V (IEC) / 150 V (UL)
2 - Rated voltage: 630 V (IEC) / 300 V (UL)a - End section ES10-ST
b - End stop BAZ1

Lateral jumper bars pre-cut poles
8 mm 0.315 in 4/6 poles
spacing
4/8 poles
4/10 poles
3/4 poles
4/7 poles
2/3 poles
4/6 poles
4/8 poles

Type

Part Number

Pkg

Weightqty(1 pce) g

Black

PC8-2
PC8-3
PC8-4
PC8-10

1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400

10
10
10
10

3.00
4.00
6.00
14.00

Black

PC8-R1
PC8-R2
PC8-R3
PC8-R4
PC8-R5
PC8-R6
PC8-R7PC8-R8

1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400842R0000
1SNA400843R0000
1SNA400849R0000
1SNA400850R0000

10
10
10
10
10
10
10
10

6.60
7.80
9.00
4.50
6.60
6.60
6.60
7.80

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values

PC81
8 mm 0.315 in spacing

PC81 lateral jumper bars
Description
Comb-type jumper bar, allows the connection of consecutive blocks or not by one compression clamp
connection.

Ordering details
Description

Color

8 mm 0.315 in spacing

10 poles

Type
Grey

PC81-10

Part Number
1SNA173523R1100

Pkg

Weightqty(1 pce) g

10

5.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Brass/polyamide
V0
I2F3-55 ... +110 °C -67 ... +230 °F-55 ... +110 °C -67 ... +230 °F-5 ... +40 °C-23 ... +104 °F

9All the main technical data provided are "manufacturer" values
RoHS

1SNK161060S0201

1SNC160537F0014

RoHS

Technical data valid for copper conductors only.

PAGE 341

Circuit separators
Screw clamp terminal block accessories

CS circuit separators
1SNK160002F0014

Description–– The CS circuit separator avoids the derating of terminal blocks when cut jumper bars JB are used,–– Compatible with feed-through terminal blocks up to 16 mm² 4 AWG,–– Without spacing loss.

Ordering details

CS

Description

0 mm 0 in spacingColor

0 mm 0 in spacing

Mounting instructions

Type

Dark grey

CS

Part Number
1SNK900101R0000

Pkg

Weightqty(1 pce) g

20

0.20

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

1SNK160003F0014

CS-R1 circuit separators

CS-R1

Description–– Ease the visual identification of the several circuits within your terminal block assemblies,–– Compatible with feed-through terminal blocks up to 35 mm² 0 AWG,–– Intermediate cover holder for CO protective cover,–– Mounting on DIN3-TH35 rail.

Ordering details

71 2.79"

69 2.72"

61.5 2.42"

Description

Color

3 mm 0.118 in spacing

CS-R1

Pkg

Weightqty(1 pce) g

1SNK900103R0000

20

5.20

Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Part Number

Pkg

Weightqty(1 pce) g

1960
22
20
10

0.23
9.00
10.00
0.20

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Mounting instructions
All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
Terminal block markers
Blank card

In polycarbonate
Blank card
Universal wire markers holder 5.2 mm 0.205 in spacing
Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Color
White

Grey

Type

MG-CPM 13 41790 1SNB041790R0512
MC512
1SNK140000R0000
MC512PA1SNK149999R0000
UMH
1SNK900611R0000

1SNK160018S0201

9

Dark grey

Part Number

Main technical data

35 1.38"

3 mm 0.118 in spacing

Type1SNK160149F0014

Shield connectors
Screw clamp terminal block accessories

SHBS/SHB

SHBS/SHB shield connectors
Description–– Ensure the continuity of your shield connection,–– Various connection solutions available: RILS cable ties, soldering, quick-connect.

Ordering details
13.67 .54"

Description

128 5.04"
SHB

Compatible with ZS feed-through terminal blocks
Compatible with ZS and ZK double deck terminal blocks

Type
SHBS
SHB

Part Number
1SNK900600R0000
1SNK900602R0000

Pkg

Weightqty(1 pce) g

20
20

3.50
4.90

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

SHBS
Rated voltage-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

IEC
320 V

UL - CSA

Ex e
125 V

All the main technical data provided are "manufacturer" values
RoHS

Accessories for screw clamp and PI-Spring terminal blocks
Description
Cable ties

Color
For SNK shield connector

Type
RILS

Part Number
1SNK900627R0000

Pkg

Weightqty(1 pce) g

10

0.30

Mounting instructions–– SHBS is directly fixed on the terminal block,–– SHB is fixed on the ES4-D2 end section,–– SHBP is directly fixed on the terminal block,–– Connect the cable shielding on the shielding connector with:–– RILS cable ties,–– quick-connect (the shield connector needs to beprepared),–– soldering iron.
9

1SNK160079S0201

10.87 .43"

SHBS
94 3.70"

Color

Technical data valid for copper conductors only.

PAGE 343

PL protecting covers
Screw clamp terminal block accessories

1SNK160096F0014

Description

PL

Mounting instructions–– Prohibit access to the screw clamps,–– Indicate live circuits.

Ordering details
Description

Color

5.2 mm 0.205 in spacing
6 mm 0.236 in spacing
8 mm 0.315 in spacing
10 mm 0.394 in spacing
16 mm 0.630 in spacing

Transparent

Type
PL5
PL6
PL8
PL10
PL16

Main technical data
Material specifications
Ambient temperature
min/max–– The mounting of the PL does not require a screwdriver,–– The dismounting of the PL requires a

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900618R0000
1SNK900619R0000
1SNK900620R0000
1SNK900621R0000
1SNK900622R0000

Pkg

Weightqty(1 pce) g

10
10
10
10
10

1.50
1.80
2.60
3.10
4.60

Mounting instructions
Polycarbonate
V2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

Flat screwdriverØ 4 mmØ 0.157 in

All the main technical data provided are "manufacturer" values
RoHS

screwdriver DIA .4 mm 0.160 in, thescrewdriver must be positionned in the
cover centered hole.

1SNK160021S0201

9

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS1SNK160110F0014

Protecting covers
Screw clamp terminal block accessories

CO protecting covers
Description–– Restrict access to your assembly with the protecting cover CO installed with KCO mounting kit (2 end stops,
2 sealing accessories),–– Compatible with SNK feed-through terminal blocks up to 35 mm² 0 AWG.

CO

Ordering details
Description
30.2 1.19"

77 3.03"Color

1 m 39.4 in length

TypeTransparent

COPart Number

Pkg

Weightqty(1 pce) g

1SNK900604R0000

1

300.00Part Number

Pkg

Weightqty(1 pce) g

1
20

47.80
27.00

Main technical data
Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Material specifications
Ambient temperature
min/max

PVC
V0-55 ... +80 °C-55 ... +80 °C-5 ... +40 °C-67 ... +176 °F-67 ... +176 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Protecting cover kits
Label

Mounting kit for cover CO

Dark grey
White

Type
KCO
PAM43020

1SNK900624R0000
1SNA235106R2600

Mounting instructions
Restrict access to the circuit by sealing the cover:–– Drill on the CO center line at 5 mm 0.197 in fromthe extremity with 5 mm 0.197 in diameter drill,–– Pass the sealing collar through the CO and KCO holes.

KCO protecting cover kits
1SNK160144F0014

Description
Mount your protecting cover with the KCO versatile mounting kit (2 end stops, 2 sealing accessories):–– Maintain the cover,–– Reliably seal the access to the terminal assembly if needed,–– Use it as well as an end stop.

Ordering details
Description
74.4 2.93"

65.7 2.59"

Mounting kit for cover CO
73.2 2.88"

37.2 1.46"

Color
Dark grey

Type
KCO

Part Number

Pkg

Weightqty(1 pce) g

1SNK900624R0000

1

47.80

Rail

G32, TH 35-7.5,
TH 35-15, TH 15-5.5
Flat screwdriverØ 4 mmØ 0.157 in

9

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

1SNK160045S0201

KCO

All the main technical data provided are "manufacturer" values
RoHS

Technical data valid for copper conductors only.

PAGE 345

1SNK160221F0014

Short circuit bridges
Screw clamp terminal block accessories

SC-JB88 mm 0.315 in spacing

SC-JB8 short circuit bridges
Description–– Allow safe short-circuiting of current Tranformers circuits,–– Insulated,–– Fully operated by screwdriver,–– Short circuited fixed position secured thanks to AJS9 tightening,–– Adapted hook shape maintains the bridge on the terminal block in the non short-circuited position,–– The orange version can be used as fixed jumpers.

Ordering details
Description

Color

8 mm 0.315 in spacing

2 poles
3 poles
4 poles
3/5 poles
3 poles
4 polesType
Yellow

OrangeSC-JB8-2
SC-JB8-3
SC-JB8-4
SC-JB8-5
SC-JB8-3-OR
SC-JB8-4-OR

Part Number
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNK900655R0000
1SNK900657R0000
1SNK900658R0000

Pkg

Weightqty(1 pce) g

25
25
25
25
25
25

2.00
3.4
4.7
4.7

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

1SNK161063S0201

9

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

AJS
4 mm 0.157 in spacing

AJS test sockets
Description–– Insulated test sockets,-- Many colors available for circuit identification,-- Compatible with standard DIA 4 mm 0.157 in test plugs:-- insulated (according to IEC 60101-031) - not insulated (with mobile protection),-- Compatible with ZS10-ST…SNK series terminal blocks, M6/8.ST...SNA series terminal blocks, D6/8.
ST.RS..Solution series terminal blocks

Ordering details
Description

Color

Test sockets DIA 4 mm 0.157 in

Type
Grey
Blue
Yellow
GreenRed
Purple
Brown
White
Black

AJS9-GRAJS9-BLAJS9
AJS9-GN
AJS9-RDAJS9-PR
AJS9-BR
AJS9-WH
AJS9-BK

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNA206682R0300
1SNA206683R0400
1SNA179726R0200
1SNA206681R0200
1SNA206720R1400
1SNA206772R0000
1SNA206782R0000
1SNA206765R0000
1SNA206680R1500

Pkg

Weightqty(1 pce) g

25
25
25
25
25
25
25
25
25

3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60

Mounting instructions
Polyamide
V0
I2F3-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueFlat screwdriverØ 3.5 mm
Ø 0.138 in

0.5 Nm ± 0.1
4.42 lb.in ± 0.88

All the main technical data provided are "manufacturer" values
RoHS

9

1SNK161064S0201

1SNC160482F0014

Test sockets
Screw clamp terminal block accessories

Technical data valid for copper conductors only.

PAGE 347

1SNK160301V0014

End sections
Pluggable terminal block accessories

EDK2.5-22

EDK2.5-22 end sections
Description–– Compatible with ZDK2.5-22 and ZDK4-22 pluggable terminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g

2.2 mm 0.087 in spacing

Dark grey

EDK2.5-22

1SNK805910R0000

20

3.08

1SNK164030V0014

EDK2.5-21 end sections
Description–– Compatible with ZDK2.5-11, ZDK2.5-11-BL and ZDK2.5-11-PE pluggable terminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g

1.5 mm 0.059 in spacing

Dark grey

EDK2.5-21

1SNK805914R0000

20

1.90

EDK2.5-21

EDK2.5-11 end sections
1SNK164029V0014

Description–– Compatible with ZD2.5-11 pluggable terminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g

1.5 mm 0.059 in spacing

Dark grey

EDK2.5-11

1SNK805915R0000

20

1.49

EDK2.5-11

EDK2.5-D end sections
1SNK164031V0014

Description–– Compatible with ZDK2.5-D2, ZDK2.5-D2-BL, ZDK2.5-D1, ZDK2.5-D1-PE and ZDK2.5-D2-PE pluggableterminal blocks.
Description

Color

Type

Part Number

Pkg
qty

Weight1 pce g2 mm 0.079 in spacing

Dark grey

EDK2.5-D

1SNK805913R0000

20

3.88

EDK2.5-D

9

Main technical data

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

All the main technical data provided are "manufacturer" values.
RoHS

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS-67 ... +230 °C-67 ... +230 °C+23 ... +104 °C
1SNK164033S0201

Material specifications

End sections
Pluggable terminal block accessories

1SNK164028V0014

ED2.5-22 end sections
Description–– Compatible with ZD2.5-22 and ZD2.5-22-PE pluggable terminal blocks.

Ordering details
Description

Color

2 mm 0.079 in spacing

ED2.5-22

Dark grey

TypePart Number

ED2.5-22

1SNK805917R0000

TypePart Number

Pkg

Weightqty(1 pce) g

20

3.64

EDS4-22

Description–– Compatible with ZDS4-22 pluggable terminal block.

Ordering details
Description

Color

0.8 mm 0.031 in spacing

Dark grey

EDS4-22

1SNK805911R0000

Pkg

Weightqty(1 pce) g

20

1.85

9

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °C-67 ... +230 °C+23 ... +104 °C

All the main technical data provided are "manufacturer" values.

1SNK164034S0201

1SNK160302V0014

EDS4-22 end sections

RoHS

Technical data valid for copper conductors only.

PAGE 349

Coding pegs - Locking devices
Pluggable terminal block accessories

COP coding pegs
1SNK160298V0014

Description–– The coding pegs prevent plugs to be inserted into the wrong circuit.

Ordering details
Description

Color

Type

Dark grey

COP-ZDPart Number
1SNK900636R0000

Pkg

Weightqty(1 pce) g

10

3.57

Main technical data

COP

Material specifications

Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions

VR locking devices
1SNK160315V0014

Description–– Automatic locking providing excellent plug withstand in case of accidental pulling,–– Lock safely one or two CDK or CDS plugs on ZDK and ZDS pluggable terminal blocks,–– Install one VR... up to 8 poles plugs assembly and two VR... up to 15 poles assembly.

Ordering details
Description

Color

VR

9.4 mm 0.370 in spacing

9.4 mm 0.370 in spacing

Main technical data
Material specifications

Ambient temperature
min/max

Type
Black

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

VR-ZD

Part Number
1SNK900637R0000

Pkg

Weightqty(1 pce) g50

6.5

Polyacetal
HB-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values.
RoHS

9

1SNK164009S0201

Mounting instructions

Technical data valid for copper conductors only.

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSPB-351

9

PAGE 351

10Part Number

Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNA007865R2600
1SNA103007R2300
1SNA103098R2600
1SNA103099R2700
1SNA113542R1000
1SNA113544R1200
1SNA114205R2000
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA116900R2700
1SNA160487R2500
1SNA160563R0000
1SNA160564R0100
1SNA160606R1400
1SNA160619R1000
1SNA160621R0200
1SNA162309R1000
1SNA162315R2500
1SNA162971R2700
1SNA162972R2000
1SNA162979R0700
1SNA162988R2100
1SNA162991R1400
1SNA163043R2100
1SNA163155R2600
1SNA163156R2700
1SNA163261R0000
1SNA163313R2400
1SNA163350R1500
1SNA163468R0000
1SNA163475R2700
1SNA163476R2000
1SNA163479R0300
1SNA163497R1600
1SNA163503R2400
1SNA163518R2200
1SNA164519R2400
1SNA164655R0400
1SNA164800R0300
1SNA167224R2700
1SNA167489R2200
1SNA167735R2700
1SNA167860R0100
1SNA168355R1300
1SNA168356R1400
1SNA168357R1500
1SNA168456R0100
1SNA168457R0200
1SNA168458R1300
1SNA168459R1400
1SNA168460R1100
1SNA168461R0600
1SNA168462R0700
1SNA168463R0000
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA168485R2700
1SNA168486R2000
1SNA168487R2100
1SNA168490R0000
1SNA168497R2300
1SNA168500R1200
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA168700R2200
1SNA168949R1700
1SNA171018R2000
1SNA173220R0500
1SNA173241R0600
1SNA173438R2400
1SNA173439R2500
1SNA173441R2700

FC2
PE
SSB20
SSB20T
PC5-2
PC5-10
AD2.5
PC8-2
PC8-3
PC8-4
BADH
HD2.5/6.2G.2G.1
HD6/9.3G.2G
HD6/9.2G.3G
HD6/8.2G.2G.1
HD6/8.2G.2G.2
HD6/9.5G
HD6/14.DG
HD6/14.SF.2G.2G
HD6/14.DHHD6/14.SDH
HD16/14.FF5.20
HD6/14.SDH.1
HD16/14.FF5.21
AL2
REH3
RTC
AL3
PC8-10
PRH2R
BJH131-10
BJH17
BJH23-10
BJH311
PEFH
BJH105
RPED
BAR
BAH22
PR3.G2
BJS13-10
BAH21
VSJ6
FC4
BAH24
BJH8-10
BJH9-10
BJH8-2
BJH8-3
BJH8-4
BJH8-5
BJH9-2
BJH9-3
BJH9-4BJH9-5
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS61-10
BJH7-2
BJH7-3
BJH7-10
PC
PR4
TGA8
TGA8
TGA8
ANT
PR5
FEHD2
EXBN2
PR30
RDJ6
BJH14-2
BJH14-3
BJH14-4

110
211
216
216
253
253
214
341
341
341
117
144
151
152
145
146
150
158
155
157
161
195
160
194
110
190
153
110
303
313
179
182
184
186
153
176
153
211
153
311
190
176
144
112
144
145
145
145
145
145
145
145
145
145
145
144
144
144
144
144
144
144
144
213
312
268
268
268
268
312
162
115
310
144
192
192
192

1SNA173449R0700
1SNA173451R2100
1SNA173452R2200
1SNA173453R2300
1SNA173454R2400
1SNA173460R0600
1SNA173461R2300
1SNA173523R1100
1SNA173627R2100
1SNA174300R1700
1SNA174784R2000
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176282R2300
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA178430R0500
1SNA178431R2200
1SNA178529R0400
1SNA178745R1400
1SNA178746R1500
1SNA178944R0400
1SNA179371R1600
1SNA179466R0600
1SNA179726R0200
1SNA187312R1400
1SNA190001R2000
1SNA190002R2100
1SNA190003R2200
1SNA190004R2300
1SNA190005R2400
1SNA190016R1600
1SNA190017R1700
1SNA190018R2000
1SNA190019R2100
1SNA190305R0500
1SNA190312R2300
1SNA190314R2500
1SNA190316R2700
1SNA190468R0000
1SNA190607R0400
1SNA191296R1100
1SNA191302R2700
1SNA193080R1200
1SNA193085R0300
1SNA193137R0300
1SNA193449R2400
1SNA193878R2200
1SNA195212R1000
1SNA196792R1700
1SNA196853R1400
1SNA196854R1500
1SNA196896R0000
1SNA196915R0200
1SNA196924R0300
1SNA196926R0500
1SNA196927R0600
1SNA196998R1600
1SNA197312R1600
1SNA198352R0700
1SNA198549R0500
1SNA198692R2500
1SNA198729R0100
1SNA199025R1400
1SNA199096R1400
1SNA199320R0400
1SNA199321R2100

BJH14-5
BJH14-10
BJH18-2
BJH18-3
BJH18-4
BJH18-5
BJH18-10
PC81-10EL6PR3.Z2
BJS6-20
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI5-10
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
RCPEB
EPR1
PR50
CBM5
CBM8
OUPAD
CN5
OUMAD
AJS9
CPM
D35/27.FF
D70/32.FF
D120/42.FF
D185/55.FF
D300/55.FF
CPUF35
CPUF70
CPUF120
CPUF185
HD2.5/6.3.2G.2G.1
HD2.5/6.3.2G.2G.1.GG
HD2.5/6.3.GG1.2G.2G
HD2.5/6.3.3G.3G.1
E4/6
E6/8
E10/16.SE10/16
FEE6-1
FEE8-2FEMT1
FEE10-16
FEH4
M6/8.STP
BNSTP1
BNC62
BNSV62
SCAD
BIE
BNF52
BNCT82BNSV82
BNF652
CPM
FEH3
FEH9
SCH3
FEH8
HD2.5/6.3.GG.1.2GG
HD2.5/6.3.GH.2G.H
COCF
COCE

192
192
192
192
192
192
192
268
111
310
111
110
110
110
110
110
111
111
111
111
111
112
112
112
112
112
316
316
311
110
110
110
268
110
300
153
196
197
198
199
200
196
197
198
199
166
163
164
162
211
212
216
213
211
212
214
213
146
214
214
115
115
111
216
116
116
116
115
153
144
155
144
158
165
167
128
119

1SNA199393R2200
1SNA199394R2300
1SNA199400R0600
1SNA199411R1400
1SNA199412R1500
1SNA199551R2000
1SNA205392R0700
1SNA205396R0300
1SNA205424R2700
1SNA205427R2200
1SNA205428R0300
1SNA205429R0400
1SNA205431R2600
1SNA205767R1600
1SNA205768R2700
1SNA205769R2000
1SNA205770R2500
1SNA205771R1200
1SNA205772R1300
1SNA205773R1400
1SNA205774R1500
1SNA205775R1600
1SNA205776R1700
1SNA205777R1000
1SNA205778R2100
1SNA205779R2200
1SNA206053R0700
1SNA206054R0000
1SNA206126R2500
1SNA206223R0600
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206721R0100
1SNA206765R0000
1SNA206772R0000
1SNA206782R0000
1SNA230000R1200
1SNA231000R0700
1SNA232000R0000
1SNA233000R0100
1SNA234000R0200
1SNA235106R2600
1SNA235155R2600
1SNA235157R2000
1SNA235158R0100
1SNA235159R0200
1SNA235510R0800
1SNA235511R0600
1SNA235512R1000
1SNA238000R1600
1SNA290451R0300
1SNA290452R0400
1SNA290453R0500
1SNA290454R0600
1SNA290455R0700
1SNA295011R1600
1SNA295012R1700
1SNA295013R1000
1SNA295014R1100
1SNA295015R1200
1SNA295298R0300
1SNA295391R2000
1SNA295392R2100
1SNA295393R2200
1SNA295394R2300
1SNA295395R2400
1SNA295396R2500
1SNA295397R2600
1SNA295398R0700
1SNA295399R0000
1SNA295400R0600
1SNA295401R2300
1SNA295402R2400
1SNA295403R2500

SCH6
INH3
FEHD1
FJH501
SCH8
SCAD5
HD4/9.F4.2
HD10/12.F5.2
FJHD40
INHD1
SCHD1
SCHD2
FJHD32
DRF6
DRF8
DRF10
DRF12
DRF16
BJS27-2
BJS27-3
BJS32-2
BJS32-3
BJS42-2
BJS42-3
BJS551-2
BJS551-3
BJMI31.2
BJMI31.3
BJMI36.2
BJMI36.3
AJS9-BK
AJS9-GN
AJS9-GRAJS9-BLAJS9-RD
AL4-M3
AJS9-WH
AJS9-PR
AJS9-BR
RC55
RC510
RC65
RC610
RC810
PAM43020
PIB2-TT
PIB2-TT-YLRCPEAD-TT
RCPEAD-TT-YL
M-W810PC
M-W610PC
M-W1010PC
RC1010
BJE762.2
BJE762.5
BJE762.10
EIP
RB-12W7
HD10/12.F5.3
HD16/14.FF5.21.3
HD16/14.FF5.20.3
HD6/13.FF4
HD6/30.F12G
HD4/10.F4.19
HD4/9.F4
HD4/9.F4.2
HD4/9.FF4
HD10/12.F5
HD10/12.F5.1
HD10/12.F5.2
HD10/12.FF5
HD35/16.F6.19
HD35/16.F6.19.1
HD70/22.F8.31
HD70/22.F8.31.1
HD70/22.F8.31.2
HD120/30.F10.31.1

192
192
147
153
153
110
177
181
181
177
177
181
177
196
197
198
199
200
196
196
197
197
198
198
199
199
239
239
240
240
302
302
302
302
302
300
302
302
302
110
110
111
111
112
345
316
316
316
316
202
201
203
239
119
119
119
119
119
179
192
193
190
154
178
176
177
189
180
181
181
191
182
183
184
185
185
187

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Index_1SNC160034C0201

Index
Part Number classification

Part Number

Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNA295405R2700
1SNA295424R1100
1SNA295425R1200
1SNA295426R1300
1SNA295427R1400
1SNA295428R2500
1SNA295429R2600
1SNA295430R2300
1SNA295431R1000
1SNA295448R0100
1SNA296351R0000
1SNA399726R0700
1SNA399730R1700
1SNA399736R0100
1SNA399742R1700
1SNA399748R2500
1SNA399749R2600
1SNA399752R1100
1SNA399787R0500
1SNA399788R1600
1SNA399802R0500
1SNA399803R0600
1SNA399804R0700
1SNA399916R2600
1SNA399963R0500
1SNA399964R0600
1SNA400014R2700
1SNA400015R2000
1SNA400018R0300
1SNA400019R0400
1SNA400061R0600
1SNA400062R0700
1SNA400063R0000
1SNA400083R2500
1SNA400142R0400
1SNA400153R0700
1SNA400154R0000
1SNA400156R0200
1SNA400240R2200
1SNA400241R1700
1SNA400315R0100
1SNA400703R1700
1SNA400704R1000
1SNA400708R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400766R1500
1SNA400767R1600
1SNA400768R2700
1SNA400782R0000
1SNA400799R0000
1SNA400800R0000
1SNA400842R0000
1SNA400843R0000
1SNA400849R0000
1SNA400850R0000
1SNA510003R0000
1SNA510005R0000
1SNA510006R0000
1SNA510024R0000
1SNA511003R0500
1SNA511024R0500
1SNA519003R0000
1SNA519004R0000
1SNA519005R0000
1SNA519103R0200
1SNA519103R0300
1SNA519103R0400
1SNA519103R1000
1SNA519104R0200
1SNA519104R0300
1SNA519104R0400
1SNA519104R0700
1SNA519104R1000
1SNA519106R0200

HD185/36.F12.31.1
FJHD40FJHD50
FJDHD
INHD1
SCHD1
SCHD2
SCHD5
FJHD32
HD120/30.F10.31
BAM2
EPR2
D1.5/6.ADO.NF
D2.5/8.ADO.NF
D1.5/6.D2.ADO.NF
D4/8.ADO.NF
D2.5/8.ADO.NF1
D2.5/8.S.ADO.NF
CPBP2
CPBP1
FEMAD3FED2AD2
FEDAD5D1.5/6.ADO.D2.NF
HD6/24.DHHD6/24.DH
ES8-CG
ES8-CG
FECPE.2ADO
FECPE.ADO
D2.5/7.ADO-CPE.NF
D2.5/7.2ADO-CPE.NF
VRADO.CPE7
D1.5/6.S.ADO.NF
BNSV62-1
D1.5/7.ADO-CPE.NF
D1.5/7.2ADO-CPE.NF
D2.5/7.ADO-CPE.NF1
D4/7.ADO-CPE.NF
D4/7.2ADO-CPE.NF
D1.5/5.ADO.NF
D2.5/7.2CPE
D2.5/7.CPE.CPE
FECPE
PC8-R1
PC8-R2
PC8-R3
PC8-R4
HD6/7.5G
HD6/7.3G.2G
HD6/7.2G.3G
HD6/22.F12G
FESDH
HD6/9.SDH.1
PC8-R5
PC8-R6
PC8-R7PC8-R8RGW2.5-V0
RGW25-M5-V0
RGW25-M6-V0
RGW6-V0RGW2.5-PE-V0
RGW6-PE-V0
E-RGW2.5
E-RGW6
E-RGW25
PC-RG2.5-2
PC-RG2.5-3
PC-RG2.5-4
PC-RG2.5-10
PC-RG6-2
PC-RG6-3
PC-RG6-4
PC-RG6-7
PC-RG6-10
PC-RG25-2

188
178
191
178
176
176
178
191
176
186
110
316
111
112
117
114
113
116
240
239
110
117
115
118
156
156
215
215
121
119
122
123
119
115
115
119
121
120
124
125
110
126
127
126
301
303
303
303
147
148
149
153
159
159
303
303
303
303
201
203
204
202
201
202
201
202
203
201
201
201
201
202
202
202
202
202
203

1SNA519200R0000
1SNA519201R0000
1SNB041090R0510
1SNB041096R0810
1SNB041790R0512
1SNB041791R0612
1SNB043196R0012
1SNB045194R1735
1SNB045490R8530
1SNB046415R0615
1SNB046915R0615
1SNB049148R1735
1SNB049198R1735
1SNB049448R8530
1SNB049498R8530
1SNK140000R0000
1SNK149999R0000
1SNK150000R0000
1SNK159999R0000
1SNK160000R0000
1SNK169999R0000
1SNK505010R0000
1SNK505020R0000
1SNK505030R0000
1SNK505060R0000
1SNK505061R0000
1SNK505062R0000
1SNK505063R0000
1SNK505064R0000
1SNK505065R0000
1SNK505066R0000
1SNK505150R0000
1SNK505210R0000
1SNK505211R0000
1SNK505212R0000
1SNK505214R0000
1SNK505215R0000
1SNK505220R0000
1SNK505230R0000
1SNK505310R0000
1SNK505311R0000
1SNK505312R0000
1SNK505313R0000
1SNK505314R0000
1SNK505315R0000
1SNK505316R0000
1SNK505320R0000
1SNK505321R0000
1SNK505330R0000
1SNK505331R0000
1SNK505910R0000
1SNK505911R0000
1SNK505912R0000
1SNK505960R0000
1SNK505961R0000
1SNK506010R0000
1SNK506011R0000
1SNK506012R0000
1SNK506013R0000
1SNK506020R0000
1SNK506021R0000
1SNK506022R0000
1SNK506030R0000
1SNK506060R0000
1SNK506061R0000
1SNK506062R0000
1SNK506063R0000
1SNK506064R0000
1SNK506065R0000
1SNK506066R0000
1SNK506067R0000
1SNK506068R0000
1SNK506150R0000
1SNK506151R0000
1SNK506152R0000
1SNK506153R0000
1SNK506210R0000

CS-RGW-S
CS-RGW-L
MG-CPM-01 41090
MG-CPM-01 41096
MG-CPM 13 41790
MG-CPM 13 41791
MG-CPMFA 43196
MG-TAR 45194
MG-TAR 45490
MG-VYT 46415
MG-VYT 46915
MG-TAA 49148
MG-TAA 49198
MG-TAA 49448
MG-TAA 49498
MC512
MC512PA
MC612
MC612PA
MC812
MC812PAZS4
ZS4-BLZS4-ORZS4-YLZS4-GNZS4-RDZS4-PRZS4-BRZS4-WHZS4-BK
ZS4-PEZS4-D2ZS4-D1ZS4-T3ZS4-D-CH-UD
ZS4-D-CH-DU
ZS4-D2-BL
ZS4-D2-OR
ZS4-S
ZS4-S-T2ZS4-S-T2.3
ZS4-SPZS4-SP-T2
ZS4-D2-S
ZS4-D2-S-T2
ZS4-S-BLZS4-S-T2-BL
ZS4-S-ORZS4-S-T2-OR
ES4
ES6-4S
ES6-3S
ES4-D2
ES4-T3
ZS6
ZS6-3S
ZS6-4SZS4-R2ZS6-BLZS6-3S-BL
ZS6-4S-BL
ZS6-ORZS6-YLZS6-GNZS6-RDZS6-PRZS6-BRZS6-WHZS6-BK
ZS6-3S-YL
ZS6-4S-YL
ZS6-PE
ZS6-3S-PE
ZS6-4S-PE
ZS4-PE-R2
ZS6-D2

201
203
201
202
19
28
93
316
316
332
332
316
316
316
316
19
19
22
22
28
28
228
228
228
228
228
228
228
228
228
228
228
284
285
294
296
297
284
284
253
254
254
260
261
290
291
253
254
253
254
228
231
230
284
294
229
230
231
278
229
230
231
229
229
229
229
229
229
229
229
230
231
229
230
231
279
286

1SNK506211R0000
1SNK506212R0000
1SNK506213R0000
1SNK506214R0000
1SNK506220R0000
1SNK506230R0000
1SNK506250R0000
1SNK506260R0000
1SNK506262R0000
1SNK506265R0000
1SNK506266R0000
1SNK506310R0000
1SNK506311R0000
1SNK506312R0000
1SNK506313R0000
1SNK506314R0000
1SNK506315R0000
1SNK506316R0000
1SNK506320R0000
1SNK506321R0000
1SNK506322R0000
1SNK506330R0000
1SNK506331R0000
1SNK506410R0000
1SNK506411R0000
1SNK506412R0000
1SNK506413R0000
1SNK506414R0000
1SNK506415R0000
1SNK506416R0000
1SNK508010R0000
1SNK508011R0000
1SNK508013R0000
1SNK508020R0000
1SNK508030R0000
1SNK508060R0000
1SNK508061R0000
1SNK508062R0000
1SNK508063R0000
1SNK508064R0000
1SNK508065R0000
1SNK508066R0000
1SNK508150R0000
1SNK508151R0000
1SNK508310R0000
1SNK508311R0000
1SNK508312R0000
1SNK508315R0000
1SNK508316R0000
1SNK508320R0000
1SNK508410R0000
1SNK508411R0000
1SNK508412R0000
1SNK508413R0000
1SNK508414R0000
1SNK508415R0000
1SNK508416R0000
1SNK508417R0000
1SNK508418R0000
1SNK508419R0000
1SNK508421R0000
1SNK508422R0000
1SNK508423R0000
1SNK508424R0000
1SNK508425R0000
1SNK508430R0000
1SNK508910R0000
1SNK508911R0000
1SNK508960R0000
1SNK510010R0000
1SNK510020R0000
1SNK510030R0000
1SNK510150R0000
1SNK512010R0000
1SNK512020R0000
1SNK512060R0000
1SNK512150R0000

ZS6-D1ZS6-D2-PE
ZS4-T3-R1
ZS6-D1-RD
ZS6-D2-BL
ZS6-D2-OR
ZS6-D1-PE
ZS6-D2-YL
ZS6-D2-RD
ZS6-D2-WH
ZS6-D2-BK
ZS4-S-R1
ZS4-S-T2-R1
ZS4-S-T2.3-R1
ZS4-SP-R1
ZS4-SP-T2-R1
ZS6-S
ZS6-S-4S-T2ZS4-S-R1-BL
ZS4-S-T2-R1-BL
ZS6-S-BLZS4-S-R1-OR
ZS4-S-T2-R1-OR
ZS4-SFZS4-SF-T2
ZS4-SF-R1
ZS4-SF-R2
ZS4-S-R2ZS4-SF-R3
ZS4-SF-R4
ZS10
ZS10-R1ZS4-R1
ZS10-BL
ZS10-ORZS10-YL
ZS10-GN
ZS10-RD
ZS10-PR
ZS10-BR
ZS10-WH
ZS10-BK
ZS10-PE
ZS10-PE-R1
ZS10-ST
ZS10-ST-T4
ZS10-ST-1
ZS10-S
ZS10-SPZS10-S-BL
ZS4-SF1ZS4-SF1-T2
ZS4-SF1-R1
ZS4-SF1-R2
ZS4-SF1-R3
ZS4-SF1-R4
ZS4-S-R3
ZS10-S-R2
ZS10-SFZS4-S-R3-T2
ZS10-SF-R1
ZS10-SF-R3
ZS4-D2-SF1-R1
ZS4-D2-SF1-R3
ZS4-D2-SF1
ZS4-SF1-OR
ES10-ST
ES4-D2-SF1
ES4-SF
ZS16
ZS16-BL
ZS16-ORZS16-PE
ZS25
ZS25-BL
ZS25-YL
ZS25-PE

287
288
295
287
286
286
286
286
286
286
286
255
256
256
262
263
257
258
255
256
257
255
256
274
275
276
277
280
276
277
232
300
272
232
232
232
232
232
232
232
232
232
232
301
302
300
300
259
264
259
268
269
270
271
270
271
273
283
281
273
282
282
293
293
292
268
300
292
268
233
233
233
233
234
234
234
234

PAGE 353

Index_1SNC160034C0201

Index
Part Number classification

10

10

Part Number

Type

Page

Part Number

Type

1SNK516010R0000
1SNK516011R0000
1SNK516020R0000
1SNK516021R0000
1SNK516030R0000
1SNK516060R0000
1SNK516063R0000
1SNK516064R0000
1SNK516150R0000
1SNK516151R0000
1SNK516170R0000
1SNK522010R0000
1SNK522020R0000
1SNK522060R0000
1SNK522150R0000
1SNK526010R0000
1SNK526020R0000
1SNK526060R0000
1SNK526150R0000
1SNK531010R0000
1SNK531020R0000
1SNK531060R0000
1SNK536010R0000
1SNK536020R0000
1SNK536060R0000
1SNK705010R0000
1SNK705011R0000
1SNK705012R0000
1SNK705020R0000
1SNK705021R0000
1SNK705022R0000
1SNK705030R0000
1SNK705031R0000
1SNK705032R0000
1SNK705060R0000
1SNK705061R0000
1SNK705062R0000
1SNK705065R0000
1SNK705066R0000
1SNK705067R0000
1SNK705068R0000
1SNK705069R0000
1SNK705072R0000
1SNK705073R0000
1SNK705074R0000
1SNK705075R0000
1SNK705076R0000
1SNK705079R0000
1SNK705080R0000
1SNK705150R0000
1SNK705151R0000
1SNK705152R0000
1SNK705210R0000
1SNK705211R0000
1SNK705212R0000
1SNK705213R0000
1SNK705214R0000
1SNK705219R0000
1SNK705220R0000
1SNK705250R0000
1SNK705310R0000
1SNK705311R0000
1SNK705312R0000
1SNK705313R0000
1SNK705320R0000
1SNK705321R0000
1SNK705330R0000
1SNK705331R0000
1SNK705510R0000
1SNK705511R0000
1SNK705512R0000
1SNK705513R0000
1SNK705550R0000
1SNK705710R0000
1SNK705711R0000
1SNK705910R0000
1SNK705911R0000

ZS35
ZS50
ZS35-BL
ZS50-BL
ZS35-ORZS50-YL
ZS50-RD
ZS50-BK
ZS35-PE
ZS50-PE
ZS35-PEN
ZS70
ZS70-BL
ZS70-YL
ZS70-PE
ZS95
ZS95-BL
ZS95-YL
ZS95-PE
ZS150
ZS150-BL
ZS150-YL
ZS240
ZS240-BL
ZS240-YL
ZK2.5
ZK2.5-3P
ZK2.5-4P
ZK2.5-BL
ZK2.5-3P-BL
ZK2.5-4P-BL
ZK2.5-OR
ZK2.5-3P-OR
ZK2.5-4P-OR
ZK2.5-YL
ZK2.5-GN
ZK2.5-RD
ZK2.5-WH
ZK2.5-BK
ZK2.5-3P-YL
ZK2.5-3P-GN
ZK2.5-3P-RD
ZK2.5-3P-WH
ZK2.5-3P-BK
ZK2.5-4P-YL
ZK2.5-4P-GN
ZK2.5-4P-RD
ZK2.5-4P-WH
ZK2.5-4P-BK
ZK2.5-PE
ZK2.5-PE-3P
ZK2.5-PE-4P
ZK2.5-D2
ZK2.5-D1
ZK2.5-D2-PE
ZK2.5-D-CH-UD
ZK2.5-D-CH-DU
ZK2.5-D-CH2-DU-RL
ZK2.5-D2-BL
ZK2.5-D1-PE
ZK2.5-S
ZK2.5-SP
ZK2.5-S-4P
ZK2.5-SP-4P
ZK2.5-S-BL
ZK2.5-S-4P-BL
ZK2.5-S-OR
ZK2.5-S-4P-OR
ZK2.5-T3
ZK2.5-T1
ZK2.5-L-L-PE
ZK2.5-L-N-PE
ZK2.5-T1-PE
ZK2.5-CH-4P-LR
ZK2.5-CH-4P-RL
EK2.5
EK2.5-3P

235
236
235
236
235
236
236
236
235
236
249
237
237
237
237
238
238
238
238
239
239
239
240
240
240
19
20
21
19
20
21
19
20
21
19
19
19
19
19
20
20
20
20
20
21
21
21
21
21
19
20
21
54
55
56
65
66
67
54
54
47
50
48
51
47
48
47
48
58
59
60
61
58
63
64
19
20

1SNK705912R0000
1SNK705913R0000
1SNK705960R0000
1SNK705961R0000
1SNK706010R0000
1SNK706011R0000
1SNK706012R0000
1SNK706020R0000
1SNK706021R0000
1SNK706022R0000
1SNK706030R0000
1SNK706031R0000
1SNK706032R0000
1SNK706060R0000
1SNK706062R0000
1SNK706066R0000
1SNK706150R0000
1SNK706151R0000
1SNK706152R0000
1SNK706310R0000
1SNK706410R0000
1SNK706411R0000
1SNK706412R0000
1SNK708010R0000
1SNK708011R0000
1SNK708020R0000
1SNK708021R0000
1SNK708030R0000
1SNK708031R0000
1SNK708060R0000
1SNK708062R0000
1SNK708066R0000
1SNK708150R0000
1SNK708151R0000
1SNK708911R0000
1SNK710010R0000
1SNK710011R0000
1SNK710020R0000
1SNK710021R0000
1SNK710030R0000
1SNK710063R0000
1SNK710064R0000
1SNK710065R0000
1SNK710067R0000
1SNK710150R0000
1SNK710151R0000
1SNK710910R0000
1SNK710911R0000
1SNK712010R0000
1SNK712011R0000
1SNK712020R0000
1SNK712021R0000
1SNK712063R0000
1SNK712064R0000
1SNK712065R0000
1SNK712067R0000
1SNK712150R0000
1SNK712151R0000
1SNK805010R0000
1SNK805013R0000
1SNK805014R0000
1SNK805015R0000
1SNK805016R0000
1SNK805017R0000
1SNK805020R0000
1SNK805025R0000
1SNK805150R0000
1SNK805152R0000
1SNK805156R0000
1SNK805212R0000
1SNK805213R0000
1SNK805214R0000
1SNK805223R0000
1SNK805250R0000
1SNK805712R0000
1SNK805713R0000
1SNK805714R0000

EK2.5-4P
EK2.5-S-4P
EK2.5-D2
EK2.5-T3
ZK4
ZK4-3P
ZK4-4P
ZK4-BLZK4-3P-BL
ZK4-4P-BL
ZK4-OR
ZK4-3P-OR
ZK4-4P-OR
ZK4-YLZK4-RDZK4-BK
ZK4-PEZK4-PE-3P
ZK4-PE-4P
ZK2.5-S-R1
ZK2.5-SF
ZK2.5-SF-R1
ZK2.5-SF-R3
ZK6
ZK6-3P
ZK6-BLZK6-3P-BL
ZK6-OR
ZK6-3P-OR
ZK6-YLZK6-RDZK6-BK
ZK6-PEZK6-PE-3P
EK6-3P
ZK10
ZK10-3P
ZK10-BL
ZK10-3P-BL
ZK10-OR
ZK10-PV
ZK10-3P-PV
ZK10-PV-BL
ZK10-3P-PV-BL
ZK10-PE
ZK10-PE-3P
EK10
EK10-3P
ZK16
ZK16-3P
ZK16-BLZK16-3P-BL
ZK16-PV
ZK16-3P-PV
ZK16-PV-BL
ZK16-3P-PV-BL
ZK16-PE
ZK16-PE-3P
ZDK2.5-22
ZDS4-22
ZDK2.5-21
ZDK2.5-11
ZD2.5-11
ZD2.5-22
ZDK2.5-22-BL
ZDK2.5-11-BL
ZDK2.5-11-PE
ZDK2.5-22-PE
ZD2.5-22-PE
ZDK2.5-D2-PE
ZDK2.5-D2
ZDK2.5-D1
ZDK2.5-D2-BL
ZDK2.5-D1-PE
CDK2.5
CDK2.5-E
CDS4INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Page
21
48
54
58
22
23
24
22
23
24
22
23
24
22
22
22
22
23
24
49
49
53
53
25
26
25
26
25
26
25
25
25
25
26
26
27
29
27
29
27
28
30
28
30
28
30
27
29
31
33
31
33
32
34
32
34
32
34
85
98
84
83
80
81
85
83
87
88
82
91
89
90
89
92
80
80
98

Part Number

Type

Page

1SNK805715R0000
1SNK805738R0000
1SNK805739R0000
1SNK805740R0000
1SNK805741R0000
1SNK805742R0000
1SNK805743R0000
1SNK805744R0000
1SNK805745R0000
1SNK805746R0000
1SNK805747R0000
1SNK805748R0000
1SNK805749R0000
1SNK805750R0000
1SNK805751R0000
1SNK805752R0000
1SNK805753R0000
1SNK805910R0000
1SNK805911R0000
1SNK805913R0000
1SNK805914R0000
1SNK805915R0000
1SNK805917R0000
1SNK806010R0000
1SNK806013R0000
1SNK806712R0000
1SNK806713R0000
1SNK806714R0000
1SNK900001R0000
1SNK900002R0000
1SNK900101R0000
1SNK900102R0000
1SNK900103R0000
1SNK900104R0000
1SNK900105R0000
1SNK900106R0000
1SNK900107R0000
1SNK900200R0000
1SNK900201R0000
1SNK900203R0000
1SNK900205R0000
1SNK900401R0000
1SNK900402R0000
1SNK900403R0000
1SNK900600R0000
1SNK900601R0000
1SNK900602R0000
1SNK900603R0000
1SNK900604R0000
1SNK900605R0000
1SNK900606R0000
1SNK900607R0000
1SNK900611R0000
1SNK900618R0000
1SNK900619R0000
1SNK900620R0000
1SNK900621R0000
1SNK900622R0000
1SNK900624R0000
1SNK900625R0000
1SNK900627R0000
1SNK900630R0000
1SNK900631R0000
1SNK900633R0000
1SNK900634R0000
1SNK900636R0000
1SNK900637R0000
1SNK900640R0000
1SNK900641R0000
1SNK900642R0000
1SNK900643R0000
1SNK900644R0000
1SNK900650R0000
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000
1SNK900655R0000

CDS4-E
CDK2.5-J
CDK2.5-J-E
CDK2.5-2P-J
CDK2.5-2P-J-E
CDK2.5-BL
CDK2.5-BL-E
CDK2.5-J-BL
CDK2.5-J-BL-E
CDK2.5-2P-J-BL
CDK2.5-2P-J-BL-E
CDK2.5-J-PE
CDK2.5-J-PE-E
CDK2.5-PE
CDK2.5-2P-J-PE
CDK2.5-2P-J-PE-E
CDK2.5-PE-E
EDK2.5-22
EDS4-22
EDK2.5-D
EDK2.5-21
EDK2.5-11
ED2.5-22
ZDK4-22
ZDS4-22-R1
CDK4
CDK4-E
CDS4-R1
BAM4
BAZ1
CS
BAZH1
CS-R1
ES-TC8
ES-TC6
CS-R2
CS-R3
TC5
TC5-R1TP2
TP4PG5
PG5-R1PG5-R2
SHBS
SHBP
SHB
JB85-3
CO
LH
LH-J
LH-R1
UMH
PL5
PL6
PL8
PL10
PL16
KCO
PT-3
RILS
MCLH
MCLH-R1
MCLH-YLMCLH-R1-YL
COP-ZD
VR-ZD
TO3.5-50
TO4-100
TO5.5-125
TO6.5-150
TO3.5-100-INS
PS-3
SC-JB8-2
SC-JB8-3
SC-JB8-4
SC-JB8-5

98
94
94
95
95
83
83
94
94
95
95
94
94
82
95
95
82
85
98
89
84
80
81
86
100
86
86
100
201
28
228
203
228
25
22
19
28
19
19
28
28
50
50
326
228
19
54
19
303
314
54
314
28
228
229
232
233
235
303
325
334
316
316
316
316
80
93
328
328
328
328
328
328
300
304
304
346

Index_1SNC160034C0201

Index
Part Number classification

IndexPart Number classification
Type

Page

Part Number

1SNK900657R0000
1SNK900658R0000
1SNK900659R0000
1SNK900660R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905310R0000
1SNK905350R0000
1SNK906302R0000
1SNK906303R0000
1SNK906304R0000
1SNK906305R0000
1SNK906310R0000
1SNK906350R0000
1SNK908302R0000
1SNK908303R0000
1SNK908304R0000
1SNK908305R0000
1SNK908310R0000
1SNK908902R0000
1SNK908903R0000
1SNK908904R0000
1SNK908905R0000
1SNK908910R0000
1SNK910302R0000
1SNK910303R0000
1SNK910304R0000
1SNK910305R0000
1SNK910310R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK916310R0000
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK922310R0000
1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK926310R0000
1SSS266202R8800
1SSS266202R9800
1SSS266203R8800
1SSS266203R9800
1SSS266204R8800
1SSS266204R9800
1SSS266205R8800
1SSS266205R9800
1SSS266206R8800
1SSS266206R9800
1SSS266207R8800
1SSS266208R8800
1SSS266208R9800
1SSS266209R8800
1SSS266210R8800
1SSS266210R9800
1SSS267202R8800
1SSS267202R9800
1SSS267203R8800
1SSS267203R9800
1SSS267204R8800
1SSS267204R9800
1SSS267205R8800
1SSS267205R9800
1SSS267206R8800
1SSS267206R9800
1SSS267207R8800
1SSS267208R8800
1SSS267208R9800
1SSS267210R8800

SC-JB8-3-OR
SC-JB8-4-OR
TO3.5-50-A
PT-ZD
JB5-2
JB5-3
JB5-4
JB5-5
JB5-10JB5-50
JB6-2
JB6-3
JB6-4
JB6-5
JB6-10JB6-50
JB8-2
JB8-3
JB8-4
JB8-5
JB8-10
JB8-2-R1
JB8-3-R1
JB8-4-R1
JB8-5-R1
JB8-10-R1
JB10-2
JB10-3
JB10-4
JB10-5
JB10-10
JB12-2
JB12-3
JB12-5
JB16-2
JB16-3
JB16-4
JB16-5
JB16-10
JB22-2
JB22-3
JB22-5
JB22-10
JB26-2
JB26-3
JB26-5
JB26-10FIC F.ADO.T1.2P.NF
FIC F.ADO.T1.B.2P.NF
FIC F.ADO.T1.3P.NF
FIC F.ADO.T1.B.3P.NF
FIC F.ADO.T1.4P.NF
FIC F.ADO.T1.B.4P.NF
FIC F.ADO.T1.5P.NF
FIC F.ADO.T1.B.5P.NF
FIC F.ADO.T1.6P.NF
FIC F.ADO.T1.B.6P.NF
FIC F.ADO.T1.7P.NF
FIC F.ADO.T1.8P.NF
FIC F.ADO.T1.B.8P.NF
FIC F.ADO.T1.9P.NF
FIC F.ADO.T1.10P.NF
FIC F.ADO.T1.B.10P.NF
FIC F.ADO.T2.2P.NF
FIC F.ADO.T2.B.2P.NF
FIC F.ADO.T2.3P.NF
FIC F.ADO.T2.B.3P.NF
FIC F.ADO.T2.4P.NF
FIC F.ADO.T2.B.4P.NF
FIC F.ADO.T2.5P.NF
FIC F.ADO.T2.B.5P.NF
FIC F.ADO.T2.6P.NF
FIC F.ADO.T2.B.6P.NF
FIC F.ADO.T2.7P.NF
FIC F.ADO.T2.8P.NF
FIC F.ADO.T2.B.8P.NF
FIC F.ADO.T2.10P.NF

346
346
328
93
19
19
19
19
19
19
22
22
22
22
22
22
25
25
25
25
25
302
302
302
302
302
27
27
27
27
27
28
28
28
235
235
235
235
235
237
237
237
237
238
238
238
238
128
129
128
129
128
129
128
129
128
129
128
128
129
128
128
129
131
132
131
132
131
132
131
132
131
132
131
131
132
131

1SSS267210R9800
FIC F.ADO.T2.B.10P.NF
132
1SSS267216R9800
FIC F.ADO.T2.B.16P.NF
132
1SSS276204R8800
FIC F.ADO.T3.4P.NF
133
1SSS276205R8800
FIC F.ADO.T3.5P.NF
133
1SSS277202R8800
FIC F.ADO.T3-.2P.NF
130
1SSS277203R8800
FIC F.ADO.T3-.3P.NF
130
1SSS277204R8800
FIC F.ADO.T3-.4P.NF
130
1SSS277205R8800
FIC F.ADO.T3-.5P.NF
130
1SSS277206R8800
FIC F.ADO.T3-.6P.NF
130
1SSS299253R2800
PT1
128
1SSS299254R2800
PT2
128
1SSS366202R4100
FIC M.ADO.T1.FI.2P.NF
134
1SSS366203R4100
FIC M.ADO.T1.FI.3P.NF
134
1SSS366204R4100
FIC M.ADO.T1.FI.4P.NF
134
1SSS366205R4100
FIC M.ADO.T1.FI.5P.NF
134
1SSS366206R4100
FIC M.ADO.T1.FI.6P.NF
134
1SSS366208R4100
FIC M.ADO.T1.FI.8P.NF
134
1SSS366210R4100
FIC M.ADO.T1.FI.10P.NF 134
1SSS367202R4100
FIC M.ADO.T2.FI.2P.NF
135
1SSS367203R4100
FIC M.ADO.T2.FI.3P.NF
135
1SSS367204R4100
FIC M.ADO.T2.FI.4P.NF
135
1SSS367205R4100
FIC M.ADO.T2.FI.5P.NF
135
1SSS367206R4100
FIC M.ADO.T2.FI.6P.NF
135
1SSS367208R4100
FIC M.ADO.T2.FI.8P.NF
135
1SSS367210R4100
FIC M.ADO.T2.FI.10P.NF 135
		

Type

Page

Part Number

Type

Page

Index_1SNC160034C0201

Part Number

PAGE 355

10

10

Type

Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

AD2.5
AJS9
AJS9-BK
AJS9-BLAJS9-BR
AJS9-GN
AJS9-GRAJS9-PR
AJS9-RDAJS9-WH
AL2
AL3
AL4-M3
ANT
BADH
BAH21
BAH22
BAH24
BAM2
BAM4
BAR
BAZ1
BAZH1
BIE
BJE762.10
BJE762.2
BJE762.5
BJH105
BJH131-10
BJH14-10
BJH14-2
BJH14-3
BJH14-4
BJH14-5
BJH17
BJH18-10
BJH18-2
BJH18-3
BJH18-4
BJH18-5
BJH23-10
BJH311
BJH7-10
BJH7-2
BJH7-3
BJH8-10
BJH8-2
BJH8-3
BJH8-4
BJH8-5
BJH9-10
BJH9-2
BJH9-3
BJH9-4BJH9-5
BJMI31.2
BJMI31.3
BJMI36.2
BJMI36.3
BJMI5-10
BJMI5-2
BJMI5-3
BJMI5-4
BJMI5-5
BJMI6-10
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI8-10
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJS13-10
BJS27-2
BJS27-3

1SNA114205R2000
1SNA179726R0200
1SNA206680R1500
1SNA206683R0400
1SNA206782R0000
1SNA206681R0200
1SNA206682R0300
1SNA206772R0000
1SNA206720R1400
1SNA206765R0000
1SNA163043R2100
1SNA163261R0000
1SNA206721R0100
1SNA168675R1400
1SNA116900R2700
1SNA167489R2200
1SNA164655R0400
1SNA168355R1300
1SNA296351R0000
1SNK900001R0000
1SNA164519R2400
1SNK900002R0000
1SNK900102R0000
1SNA196915R0200
1SNA290453R0500
1SNA290451R0300
1SNA290452R0400
1SNA163503R2400
1SNA163468R0000
1SNA173451R2100
1SNA173438R2400
1SNA173439R2500
1SNA173441R2700
1SNA173449R0700
1SNA163475R2700
1SNA173461R2300
1SNA173452R2200
1SNA173453R2300
1SNA173454R2400
1SNA173460R0600
1SNA163476R2000
1SNA163479R0300
1SNA168490R0000
1SNA168486R2000
1SNA168487R2100
1SNA168356R1400
1SNA168456R0100
1SNA168457R0200
1SNA168458R1300
1SNA168459R1400
1SNA168357R1500
1SNA168460R1100
1SNA168461R0600
1SNA168462R0700
1SNA168463R0000
1SNA206053R0700
1SNA206054R0000
1SNA206126R2500
1SNA206223R0600
1SNA176282R2300
1SNA176278R1600
1SNA176279R1700
1SNA176280R0500
1SNA176281R2200
1SNA176667R0400
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176673R0200
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA167224R2700
1SNA205772R1300
1SNA205773R1400

214
300
302
302
302
302
302
302
302
302
110
110
300
268
117
176
153
144
110
201
211
28
203
216
119
119
119
176
179
192
192
192
192
192
182
192
192
192
192
192
184
186
144
144
144
145
145
145
145
145
145
145
145
145
145
239
239
240
240
110
110
110
110
110
111
111
111
111
111
112
112
112
112
112
190
196
196

BJS32-2
BJS32-3
BJS42-2
BJS42-3
BJS551-2
BJS551-3
BJS61-10
BJS61-2
BJS61-3
BJS61-4
BJS61-5
BJS6-20
BNC62
BNCT82
BNF52
BNF652
BNSTP1BNSV62BNSV62-1
BNSV82
CBM5
CBM8
CDK2.5
CDK2.5-2P-J
CDK2.5-2P-J-BL
CDK2.5-2P-J-BL-E
CDK2.5-2P-J-E
CDK2.5-2P-J-PE
CDK2.5-2P-J-PE-E
CDK2.5-BL
CDK2.5-BL-E
CDK2.5-E
CDK2.5-J
CDK2.5-J-BL
CDK2.5-J-BL-E
CDK2.5-J-E
CDK2.5-J-PE
CDK2.5-J-PE-E
CDK2.5-PE
CDK2.5-PE-E
CDK4
CDK4-E
CDS4
CDS4-E
CDS4-R1
CN5
CO
COCE
COCF
COP-ZD
CPBP1
CPBP2
CPM

1SNA205774R1500
1SNA205775R1600
1SNA205776R1700
1SNA205777R1000
1SNA205778R2100
1SNA205779R2200
1SNA168485R2700
1SNA168481R2300
1SNA168482R2400
1SNA168483R2500
1SNA168484R2600
1SNA174784R2000
1SNA196853R1400
1SNA196926R0500
1SNA196924R0300
1SNA196998R1600
1SNA196792R1700
1SNA196854R1500
1SNA400142R0400
1SNA196927R0600
1SNA178745R1400
1SNA178746R1500
1SNK805712R0000
1SNK805740R0000
1SNK805746R0000
1SNK805747R0000
1SNK805741R0000
1SNK805751R0000
1SNK805752R0000
1SNK805742R0000
1SNK805743R0000
1SNK805713R0000
1SNK805738R0000
1SNK805744R0000
1SNK805745R0000
1SNK805739R0000
1SNK805748R0000
1SNK805749R0000
1SNK805750R0000
1SNK805753R0000
1SNK806712R0000
1SNK806713R0000
1SNK805714R0000
1SNK805715R0000
1SNK806714R0000
1SNA179371R1600
1SNK900604R0000
1SNA199321R2100
1SNA199320R0400
1SNK900636R0000
1SNA399788R1600
1SNA399787R0500
1SNA187312R1400
1SNA197312R1600
1SNA190018R2000
1SNA190019R2100
1SNA190016R1600
1SNA190017R1700
1SNK900101R0000
1SNK900103R0000
1SNK900106R0000
1SNK900107R0000
1SNA519201R0000
1SNA519200R0000
1SNA400315R0100
1SNA399916R2600
1SNA399730R1700
1SNA399742R1700
1SNA400083R2500
1SNA400154R0000
1SNA400153R0700
1SNA190003R2200
1SNA190004R2300
1SNA400062R0700
1SNA400703R1700
1SNA400061R0600
1SNA400156R0200

197
197
198
198
199
199
144
144
144
144
144
111
115
116
116
115
214
115
115
116
110
110
80
95
95
95
95
95
95
83
83
80
94
94
94
94
94
94
82
82
86
86
98
98
100
268
303
119
128
80
239
240
153
153
198
199
196
197
228
228
19
28
203
201
110
118
111
117
115
121
119
198
199
123
126
122
120

D2.5/7.CPE.CPE
D2.5/8.ADO.NF
D2.5/8.ADO.NF1
D2.5/8.S.ADO.NF
D300/55.FF
D35/27.FF
D4/7.2ADO-CPE.NF
D4/7.ADO-CPE.NF
D4/8.ADO.NF
D70/32.FF
DRF10
DRF12
DRF16
DRF6
DRF8
E10/16
E10/16.S
E4/6
E6/8
ED2.5-22
EDK2.5-11
EDK2.5-21
EDK2.5-22
EDK2.5-D
EDS4-22
EIP
EK10
EK10-3P
EK2.5
EK2.5-3P
EK2.5-4P
EK2.5-D2
EK2.5-S-4P
EK2.5-T3
EK6-3P
EL6
EPR1
EPR2
E-RGW2.5
E-RGW25
E-RGW6
ES10-ST
ES4
ES4-D2
ES4-D2-SF1
ES4-SF
ES4-T3
ES6-3S
ES6-4S
ES8-CG

1SNA400704R1000
1SNA399736R0100
1SNA399749R2600
1SNA399752R1100
1SNA190005R2400
1SNA190001R2000
1SNA400241R1700
1SNA400240R2200
1SNA399748R2500
1SNA190002R2100
1SNA205769R2000
1SNA205770R2500
1SNA205771R1200
1SNA205767R1600
1SNA205768R2700
1SNA191302R2700
1SNA191296R1100
1SNA190468R0000
1SNA190607R0400
1SNK805917R0000
1SNK805915R0000
1SNK805914R0000
1SNK805910R0000
1SNK805913R0000
1SNK805911R0000
1SNA290454R0600
1SNK710910R0000
1SNK710911R0000
1SNK705910R0000
1SNK705911R0000
1SNK705912R0000
1SNK705960R0000
1SNK705913R0000
1SNK705961R0000
1SNK708911R0000
1SNA173627R2100
1SNA178431R2200
1SNA399726R0700
1SNA519003R0000
1SNA519005R0000
1SNA519004R0000
1SNK508910R0000
1SNK505910R0000
1SNK505960R0000
1SNK508911R0000
1SNK508960R0000
1SNK505961R0000
1SNK505912R0000
1SNK505911R0000
1SNA400014R2700
1SNA400015R2000
1SNK900105R0000
1SNK900104R0000
1SNA171018R2000
1SNA007865R2600
1SNA167860R0100
1SNA400708R2400
1SNA400018R0300
1SNA400019R0400
1SNA399803R0600
1SNA399804R0700
1SNA193449R2400
1SNA193080R1200
1SNA193085R0300
1SNA198352R0700
1SNA193878R2200
1SNA198729R0100
1SNA198549R0500
1SNA199400R0600
1SNA168949R1700
1SNA399802R0500
1SNA193137R0300
1SNA400799R0000
1SSS266210R8800
1SSS266202R8800
1SSS266203R8800
1SSS266204R8800

127
112
113
116
200
196
125
124
114
197
198
199
200
196
197
213
216
211
212
81
80
84
85
89
98
119
27
29
19
20
21
54
48
58
26
111
316
316
201
203
202
300
228
284
292
268
294
230
231
215
215
22
25
115
110
112
126
121
119
117
115
213
211
212
144
146
158
155
147
162
110
214
159
128
128
128
128

CPUF120
CPUF185
CPUF35
CPUF70
CS
CS-R1
CS-R2
CS-R3
CS-RGW-L
CS-RGW-S
D1.5/5.ADO.NF
D1.5/6.ADO.D2.NF
D1.5/6.ADO.NF
D1.5/6.D2.ADO.NF
D1.5/6.S.ADO.NF
D1.5/7.2ADO-CPE.NF
D1.5/7.ADO-CPE.NF
D120/42.FF
D185/55.FF
D2.5/7.2ADO-CPE.NF
D2.5/7.2CPE
D2.5/7.ADO-CPE.NF
D2.5/7.ADO-CPE.NF1

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

ES-TC6
ES-TC8
EXBN2
FC2
FC4
FECPE
FECPE.2ADO
FECPE.ADO
FED2AD2
FEDAD5
FEE10-16
FEE6-1
FEE8-2
FEH3
FEH4
FEH8
FEH9
FEHD1
FEHD2
FEMAD3FEMT1FESDHFIC F.ADO.T1.10P.NF
FIC F.ADO.T1.2P.NF
FIC F.ADO.T1.3P.NF
FIC F.ADO.T1.4P.NF

Index_1SNC160034C0201

Index
Type classification

TypePart Number

Page

Type

Part Number

Page

Type

Part Number

Page

FIC F.ADO.T1.5P.NF
FIC F.ADO.T1.6P.NF
FIC F.ADO.T1.7P.NF
FIC F.ADO.T1.8P.NF
FIC F.ADO.T1.9P.NF
FIC F.ADO.T1.B.10P.NF
FIC F.ADO.T1.B.2P.NF
FIC F.ADO.T1.B.3P.NF
FIC F.ADO.T1.B.4P.NF
FIC F.ADO.T1.B.5P.NF
FIC F.ADO.T1.B.6P.NF
FIC F.ADO.T1.B.8P.NF
FIC F.ADO.T2.10P.NF
FIC F.ADO.T2.2P.NF
FIC F.ADO.T2.3P.NF
FIC F.ADO.T2.4P.NF
FIC F.ADO.T2.5P.NF
FIC F.ADO.T2.6P.NF
FIC F.ADO.T2.7P.NF
FIC F.ADO.T2.8P.NF
FIC F.ADO.T2.B.10P.NF
FIC F.ADO.T2.B.16P.NF
FIC F.ADO.T2.B.2P.NF
FIC F.ADO.T2.B.3P.NF
FIC F.ADO.T2.B.4P.NF
FIC F.ADO.T2.B.5P.NF
FIC F.ADO.T2.B.6P.NF
FIC F.ADO.T2.B.8P.NF
FIC F.ADO.T3-.2P.NF
FIC F.ADO.T3-.3P.NF
FIC F.ADO.T3.4P.NF
FIC F.ADO.T3-.4P.NF
FIC F.ADO.T3.5P.NF
FIC F.ADO.T3-.5P.NF
FIC F.ADO.T3-.6P.NF
FIC M.ADO.T1.FI.10P.NF
FIC M.ADO.T1.FI.2P.NF
FIC M.ADO.T1.FI.3P.NF
FIC M.ADO.T1.FI.4P.NF
FIC M.ADO.T1.FI.5P.NF
FIC M.ADO.T1.FI.6P.NF
FIC M.ADO.T1.FI.8P.NF
FIC M.ADO.T2.FI.10P.NF
FIC M.ADO.T2.FI.2P.NF
FIC M.ADO.T2.FI.3P.NF
FIC M.ADO.T2.FI.4P.NF
FIC M.ADO.T2.FI.5P.NF
FIC M.ADO.T2.FI.6P.NF
FIC M.ADO.T2.FI.8P.NF
FJDHD
FJH501
FJHD32

1SSS266205R8800
1SSS266206R8800
1SSS266207R8800
1SSS266208R8800
1SSS266209R8800
1SSS266210R9800
1SSS266202R9800
1SSS266203R9800
1SSS266204R9800
1SSS266205R9800
1SSS266206R9800
1SSS266208R9800
1SSS267210R8800
1SSS267202R8800
1SSS267203R8800
1SSS267204R8800
1SSS267205R8800
1SSS267206R8800
1SSS267207R8800
1SSS267208R8800
1SSS267210R9800
1SSS267216R9800
1SSS267202R9800
1SSS267203R9800
1SSS267204R9800
1SSS267205R9800
1SSS267206R9800
1SSS267208R9800
1SSS277202R8800
1SSS277203R8800
1SSS276204R8800
1SSS277204R8800
1SSS276205R8800
1SSS277205R8800
1SSS277206R8800
1SSS366210R4100
1SSS366202R4100
1SSS366203R4100
1SSS366204R4100
1SSS366205R4100
1SSS366206R4100
1SSS366208R4100
1SSS367210R4100
1SSS367202R4100
1SSS367203R4100
1SSS367204R4100
1SSS367205R4100
1SSS367206R4100
1SSS367208R4100
1SNA295426R1300
1SNA199411R1400
1SNA205431R2600
1SNA295431R1000
1SNA205424R2700
1SNA295424R1100
1SNA295425R1200
1SNA295394R2300
1SNA295395R2400
1SNA205396R0300
1SNA295396R2500
1SNA295011R1600
1SNA295397R2600
1SNA295448R0100
1SNA295403R2500
1SNA162979R0700
1SNA295013R1000
1SNA162991R1400
1SNA295012R1700
1SNA295405R2700
1SNA160487R2500
1SNA190305R0500
1SNA190312R2300
1SNA190316R2700
1SNA199025R1400
1SNA190314R2500
1SNA199096R1400
1SNA295398R0700

128
128
128
128
128
129
129
129
129
129
129
129
131
131
131
131
131
131
131
131
132
132
132
132
132
132
132
132
130
130
133
130
133
130
130
134
134
134
134
134
134
134
135
135
135
135
135
135
135
178
153
177
176
181
178
191
180
181
181
181
179
191
186
187
195
193
194
192
188
144
166
163
162
165
164
167
182

HD35/16.F6.19.1
HD4/10.F4.19
HD4/9.F4
HD4/9.F4.2

1SNA295399R0000
1SNA295298R0300
1SNA295391R2000
1SNA205392R0700
1SNA295392R2100
1SNA295393R2200
1SNA295014R1100
1SNA162309R1000
1SNA162971R2700
1SNA162972R2000
1SNA162988R2100
1SNA162315R2500
1SNA400782R0000
1SNA399963R0500
1SNA399964R0600
1SNA295015R1200
1SNA400768R2700
1SNA400767R1600
1SNA400766R1500
1SNA160606R1400
1SNA160619R1000
1SNA160564R0100
1SNA160563R0000
1SNA160621R0200
1SNA400800R0000
1SNA295400R0600
1SNA295401R2300
1SNA295402R2400
1SNA199394R2300
1SNA205427R2200
1SNA295427R1400
1SNK910310R0000
1SNK910302R0000
1SNK910303R0000
1SNK910304R0000
1SNK910305R0000
1SNK912302R0000
1SNK912303R0000
1SNK912305R0000
1SNK916310R0000
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK922310R0000
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK926310R0000
1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK905310R0000
1SNK905302R0000
1SNK905303R0000
1SNK905304R0000
1SNK905305R0000
1SNK905350R0000
1SNK906310R0000
1SNK906302R0000
1SNK906303R0000
1SNK906304R0000
1SNK906305R0000
1SNK906350R0000
1SNK908310R0000
1SNK908910R0000
1SNK908302R0000
1SNK908902R0000
1SNK908303R0000
1SNK908903R0000
1SNK908304R0000
1SNK908904R0000
1SNK908305R0000
1SNK900603R0000
1SNK908905R0000
1SNK900624R0000
1SNK900605R0000

183
178
176
177
177
189
190
158
157
161
160
155
153
156
156
154
149
148
147
145
146
152
151
150
159
184
185
185
192
177
176
27
27
27
27
27
28
28
28
235
235
235
235
235
237
237
237
237
238
238
238
238
19
19
19
19
19
19
22
22
22
22
22
22
25
302
25
302
25
302
25
302
25
19
302
303
314

LH-J
LH-R1
M6/8.STP
MC512
MC512PA
MC612
MC612PA
MC812
MC812PA
MCLH
MCLH-R1
MCLH-R1-YL
MCLH-YL
MG-CPM 13 41790
MG-CPM 13 41791
MG-CPM-01 41090
MG-CPM-01 41096
MG-CPMFA 43196
MG-TAA 49148
MG-TAA 49198
MG-TAA 49448
MG-TAA 49498
MG-TAR 45194
MG-TAR 45490
MG-VYT 46415
MG-VYT 46915
M-W1010PC
M-W610PC
M-W810PC
OUMAD
OUPAD
PAM43020
PC
PC5-10
PC5-2
PC8-10PC81-10
PC8-2
PC8-3
PC8-4
PC8-R1
PC8-R2
PC8-R3
PC8-R4
PC8-R5
PC8-R6
PC8-R7PC8-R8
PC-RG2.5-10
PC-RG2.5-2
PC-RG2.5-3
PC-RG2.5-4
PC-RG25-2
PC-RG6-10
PC-RG6-2
PC-RG6-3
PC-RG6-4
PC-RG6-7
PE
PEFH
PG5
PG5-R1PG5-R2
PIB2-TT
PIB2-TT-YL
PL10
PL16
PL5
PL6
PL8
PR3.G2PR3.Z2
PR30
PR4
PR5
PR50
PRH2R

1SNK900606R0000
1SNK900607R0000
1SNA195212R1000
1SNK140000R0000
1SNK149999R0000
1SNK150000R0000
1SNK159999R0000
1SNK160000R0000
1SNK169999R0000
1SNK900630R0000
1SNK900631R0000
1SNK900634R0000
1SNK900633R0000
1SNB041790R0512
1SNB041791R0612
1SNB041090R0510
1SNB041096R0810
1SNB043196R0012
1SNB049148R1735
1SNB049198R1735
1SNB049448R8530
1SNB049498R8530
1SNB045194R1735
1SNB045490R8530
1SNB046415R0615
1SNB046915R0615
1SNA235512R1000
1SNA235511R0600
1SNA235510R0800
1SNA179466R0600
1SNA178944R0400
1SNA235106R2600
1SNA168497R2300
1SNA113544R1200
1SNA113542R1000
1SNA163313R2400
1SNA173523R1100
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400842R0000
1SNA400843R0000
1SNA400849R0000
1SNA400850R0000
1SNA519103R1000
1SNA519103R0200
1SNA519103R0300
1SNA519103R0400
1SNA519106R0200
1SNA519104R1000
1SNA519104R0200
1SNA519104R0300
1SNA519104R0400
1SNA519104R0700
1SNA103007R2300
1SNA163497R1600
1SNK900401R0000
1SNK900402R0000
1SNK900403R0000
1SNA235155R2600
1SNA235157R2000
1SNK900621R0000
1SNK900622R0000
1SNK900618R0000
1SNK900619R0000
1SNK900620R0000
1SNA164800R0300
1SNA174300R1700
1SNA173220R0500
1SNA168500R1200
1SNA168700R2200
1SNA178529R0400
1SNA163350R1500

54
314
214
19
19
22
22
28
28
316
316
316
316
19
28
201
202
93
316
316
316
316
316
316
332
332
203
201
202
110
110
345
213
253
253
303
268
341
341
341
301
303
303
303
303
303
303
303
201
201
201
201
203
202
202
202
202
202
211
153
50
50
326
316
316
233
235
228
229
232
311
310
310
312
312
311
313

FJHD40FJHD50HD10/12.F5
HD10/12.F5.1
HD10/12.F5.2
HD10/12.F5.3
HD10/12.FF5
HD120/30.F10.31
HD120/30.F10.31.1
HD16/14.FF5.20
HD16/14.FF5.20.3
HD16/14.FF5.21
HD16/14.FF5.21.3
HD185/36.F12.31.1
HD2.5/6.2G.2G.1
HD2.5/6.3.2G.2G.1
HD2.5/6.3.2G.2G.1.GG
HD2.5/6.3.3G.3G.1
HD2.5/6.3.GG.1.2GG
HD2.5/6.3.GG1.2G.2G
HD2.5/6.3.GH.2G.H
HD35/16.F6.19

HD4/9.FF4
HD6/13.FF4
HD6/14.DG
HD6/14.DHHD6/14.SDH
HD6/14.SDH.1
HD6/14.SF.2G.2G
HD6/22.F12G
HD6/24.DHHD6/30.F12G
HD6/7.2G.3G
HD6/7.3G.2G
HD6/7.5G
HD6/8.2G.2G.1
HD6/8.2G.2G.2
HD6/9.2G.3G
HD6/9.3G.2G
HD6/9.5G
HD6/9.SDH.1
HD70/22.F8.31
HD70/22.F8.31.1
HD70/22.F8.31.2
INH3
INHD1
JB10-10
JB10-2
JB10-3
JB10-4
JB10-5
JB12-2
JB12-3
JB12-5
JB16-10
JB16-2
JB16-3
JB16-4
JB16-5
JB22-10
JB22-2
JB22-3
JB22-5
JB26-10
JB26-2
JB26-3
JB26-5JB5-10
JB5-2
JB5-3
JB5-4
JB5-5
JB5-50
JB6-10
JB6-2
JB6-3
JB6-4
JB6-5
JB6-50
JB8-10
JB8-10-R1
JB8-2
JB8-2-R1
JB8-3
JB8-3-R1
JB8-4
JB8-4-R1
JB8-5
JB85-3
JB8-5-R1
KCO
LH

PAGE 357

Index_1SNC160034C0201

Index
Type classification

10

Type

Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

PS-3
PT1
PT2
PT-3
PT-ZD
RB-12W7
RC1010
RC510
RC55
RC610
RC65
RC810
RCPEAD-TT
RCPEAD-TT-YL
RCPEB
RDJ6
REH3
RGW2.5-PE-V0
RGW2.5-V0
RGW25-M5-V0
RGW25-M6-V0
RGW6-PE-V0
RGW6-V0
RILS
RPED
RTC
SCAD
SCAD5
SCH3
SCH6
SCH8
SCHD1

1SNK900650R0000
1SSS299253R2800
1SSS299254R2800
1SNK900625R0000
1SNK900660R0000
1SNA290455R0700
1SNA238000R1600
1SNA231000R0700
1SNA230000R1200
1SNA233000R0100
1SNA232000R0000
1SNA234000R0200
1SNA235158R0100
1SNA235159R0200
1SNA178430R0500
1SNA173241R0600
1SNA163155R2600
1SNA511003R0500
1SNA510003R0000
1SNA510005R0000
1SNA510006R0000
1SNA511024R0500
1SNA510024R0000
1SNK900627R0000
1SNA163518R2200
1SNA163156R2700
1SNA196896R0000
1SNA199551R2000
1SNA198692R2500
1SNA199393R2200
1SNA199412R1500
1SNA205428R0300
1SNA295428R2500
1SNA205429R0400
1SNA295429R2600
1SNA295430R2300
1SNK900652R0000
1SNK900653R0000
1SNK900657R0000
1SNK900654R0000
1SNK900658R0000
1SNK900655R0000
1SNK900602R0000
1SNK900601R0000
1SNK900600R0000
1SNA103098R2600
1SNA103099R2700
1SNK900200R0000
1SNK900201R0000
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNK900644R0000
1SNK900640R0000
1SNK900659R0000
1SNK900641R0000
1SNK900642R0000
1SNK900643R0000
1SNK900203R0000
1SNK900205R0000
1SNK900611R0000
1SNA400063R0000
1SNK900637R0000
1SNA167735R2700
1SNK805016R0000
1SNK805017R0000
1SNK805156R0000
1SNK805015R0000
1SNK805025R0000
1SNK805150R0000
1SNK805014R0000
1SNK805010R0000
1SNK805020R0000
1SNK805152R0000
1SNK805214R0000
1SNK805250R0000
1SNK805213R0000

328
128
128
325
93
119
239
110
110
111
111
112
316
316
316
144
190
201
201
203
204
202
202
334
153
153
111
110
144
192
153
177
176
181
178
191
300
304
346
304
346
346
54
19
228
216
216
19
19
268
268
268
328
328
328
328
328
328
28
28
28
119
93
144
80
81
82
83
83
87
84
85
85
88
90
92
89

ZDK2.5-D2-BL
ZDK2.5-D2-PE
ZDK4-22
ZDS4-22
ZDS4-22-R1
ZK10
ZK10-3P
ZK10-3P-BL
ZK10-3P-PV
ZK10-3P-PV-BL
ZK10-BL
ZK10-OR
ZK10-PE
ZK10-PE-3P
ZK10-PV
ZK10-PV-BL
ZK16
ZK16-3P
ZK16-3P-BL
ZK16-3P-PV
ZK16-3P-PV-BL
ZK16-BLZK16-PE
ZK16-PE-3P
ZK16-PV
ZK16-PV-BL
ZK2.5
ZK2.5-3P
ZK2.5-3P-BK
ZK2.5-3P-BL
ZK2.5-3P-GN
ZK2.5-3P-OR
ZK2.5-3P-RD
ZK2.5-3P-WH
ZK2.5-3P-YL
ZK2.5-4P
ZK2.5-4P-BK
ZK2.5-4P-BL
ZK2.5-4P-GN
ZK2.5-4P-OR
ZK2.5-4P-RD
ZK2.5-4P-WH
ZK2.5-4P-YL
ZK2.5-BK
ZK2.5-BL
ZK2.5-CH-4P-LR
ZK2.5-CH-4P-RL
ZK2.5-D1
ZK2.5-D1-PE
ZK2.5-D2
ZK2.5-D2-BL
ZK2.5-D2-PE
ZK2.5-D-CH2-DU-RL
ZK2.5-D-CH-DU
ZK2.5-D-CH-UD
ZK2.5-GN
ZK2.5-L-L-PE
ZK2.5-L-N-PE
ZK2.5-OR
ZK2.5-PE
ZK2.5-PE-3P
ZK2.5-PE-4P
ZK2.5-RD
ZK2.5-S
ZK2.5-S-4P
ZK2.5-S-4P-BL
ZK2.5-S-4P-OR
ZK2.5-S-BL
ZK2.5-SF
ZK2.5-SF-R1
ZK2.5-SF-R3
ZK2.5-S-OR
ZK2.5-SP
ZK2.5-SP-4P
ZK2.5-S-R1
ZK2.5-T1
ZK2.5-T1-PE

1SNK805223R0000
1SNK805212R0000
1SNK806010R0000
1SNK805013R0000
1SNK806013R0000
1SNK710010R0000
1SNK710011R0000
1SNK710021R0000
1SNK710064R0000
1SNK710067R0000
1SNK710020R0000
1SNK710030R0000
1SNK710150R0000
1SNK710151R0000
1SNK710063R0000
1SNK710065R0000
1SNK712010R0000
1SNK712011R0000
1SNK712021R0000
1SNK712064R0000
1SNK712067R0000
1SNK712020R0000
1SNK712150R0000
1SNK712151R0000
1SNK712063R0000
1SNK712065R0000
1SNK705010R0000
1SNK705011R0000
1SNK705073R0000
1SNK705021R0000
1SNK705068R0000
1SNK705031R0000
1SNK705069R0000
1SNK705072R0000
1SNK705067R0000
1SNK705012R0000
1SNK705080R0000
1SNK705022R0000
1SNK705075R0000
1SNK705032R0000
1SNK705076R0000
1SNK705079R0000
1SNK705074R0000
1SNK705066R0000
1SNK705020R0000
1SNK705710R0000
1SNK705711R0000
1SNK705211R0000
1SNK705250R0000
1SNK705210R0000
1SNK705220R0000
1SNK705212R0000
1SNK705219R0000
1SNK705214R0000
1SNK705213R0000
1SNK705061R0000
1SNK705512R0000
1SNK705513R0000
1SNK705030R0000
1SNK705150R0000
1SNK705151R0000
1SNK705152R0000
1SNK705062R0000
1SNK705310R0000
1SNK705312R0000
1SNK705321R0000
1SNK705331R0000
1SNK705320R0000
1SNK706410R0000
1SNK706411R0000
1SNK706412R0000
1SNK705330R0000
1SNK705311R0000
1SNK705313R0000
1SNK706310R0000
1SNK705511R0000
1SNK705550R0000

89
91
86
98
100
27
29
29
30
30
27
27
28
30
28
28
31
33
33
34
34
31
32
34
32
32
19
20
20
20
20
20
20
20
20
21
21
21
21
21
21
21
21
19
19
63
64
55
54
54
54
56
67
66
65
19
60
61
19
19
20
21
19
47
48
48
48
47
49
53
53
47
50
51
49
59
58

ZK2.5-T3
ZK2.5-WH
ZK2.5-YL
ZK4
ZK4-3P
ZK4-3P-BL
ZK4-3P-OR
ZK4-4P
ZK4-4P-BL
ZK4-4P-OR
ZK4-BK
ZK4-BLZK4-ORZK4-PEZK4-PE-3P
ZK4-PE-4P
ZK4-RDZK4-YL
ZK6
ZK6-3P
ZK6-3P-BL
ZK6-3P-OR
ZK6-BKZK6-BLZK6-ORZK6-PEZK6-PE-3P
ZK6-RDZK6-YLZS10
ZS10-BK
ZS10-BL
ZS10-BR
ZS10-GN
ZS10-ORZS10-PE
ZS10-PE-R1
ZS10-PR
ZS10-R1
ZS10-RD
ZS10-S
ZS10-S-BL
ZS10-SF
ZS10-SF-R1
ZS10-SF-R3
ZS10-SPZS10-S-R2
ZS10-ST
ZS10-ST-1
ZS10-ST-T4
ZS10-WH
ZS10-YL
ZS150
ZS150-BL
ZS150-YL
ZS16
ZS16-BL
ZS16-ORZS16-PE
ZS240
ZS240-BL
ZS240-YL
ZS25
ZS25-BL
ZS25-PE
ZS25-YL
ZS35
ZS35-BL
ZS35-ORZS35-PE
ZS35-PEN
ZS4ZS4-BK
ZS4-BLZS4-BRZS4-D1ZS4-D2

1SNK705510R0000
1SNK705065R0000
1SNK705060R0000
1SNK706010R0000
1SNK706011R0000
1SNK706021R0000
1SNK706031R0000
1SNK706012R0000
1SNK706022R0000
1SNK706032R0000
1SNK706066R0000
1SNK706020R0000
1SNK706030R0000
1SNK706150R0000
1SNK706151R0000
1SNK706152R0000
1SNK706062R0000
1SNK706060R0000
1SNK708010R0000
1SNK708011R0000
1SNK708021R0000
1SNK708031R0000
1SNK708066R0000
1SNK708020R0000
1SNK708030R0000
1SNK708150R0000
1SNK708151R0000
1SNK708062R0000
1SNK708060R0000
1SNK508010R0000
1SNK508066R0000
1SNK508020R0000
1SNK508064R0000
1SNK508061R0000
1SNK508030R0000
1SNK508150R0000
1SNK508151R0000
1SNK508063R0000
1SNK508011R0000
1SNK508062R0000
1SNK508315R0000
1SNK508320R0000
1SNK508418R0000
1SNK508421R0000
1SNK508422R0000
1SNK508316R0000
1SNK508417R0000
1SNK508310R0000
1SNK508312R0000
1SNK508311R0000
1SNK508065R0000
1SNK508060R0000
1SNK531010R0000
1SNK531020R0000
1SNK531060R0000
1SNK510010R0000
1SNK510020R0000
1SNK510030R0000
1SNK510150R0000
1SNK536010R0000
1SNK536020R0000
1SNK536060R0000
1SNK512010R0000
1SNK512020R0000
1SNK512150R0000
1SNK512060R0000
1SNK516010R0000
1SNK516020R0000
1SNK516030R0000
1SNK516150R0000
1SNK516170R0000
1SNK505010R0000
1SNK505066R0000
1SNK505020R0000
1SNK505064R0000
1SNK505211R0000
1SNK505210R0000

58
19
19
22
23
23
23
24
24
24
22
22
22
22
23
24
22
22
25
26
26
26
25
25
25
25
26
25
25
232
232
232
232
232
232
232
301
232
300
232
259
259
281
282
282
264
283
302
300
300
232
232
239
239
239
233
233
233
233
240
240
240
234
234
234
234
235
235
235
235
249
228
228
228
228
285
284

SCHD2
SCHD5
SC-JB8-2
SC-JB8-3
SC-JB8-3-OR
SC-JB8-4
SC-JB8-4-OR
SC-JB8-5
SHB
SHBP
SHBS
SSB20
SSB20TTC5
TC5-R1
TGA8

10

TO3.5-100-INS
TO3.5-50
TO3.5-50-A
TO4-100
TO5.5-125
TO6.5-150
TP2
TP4
UMH
VRADO.CPE7
VR-ZD
VSJ6
ZD2.5-11
ZD2.5-22
ZD2.5-22-PE
ZDK2.5-11
ZDK2.5-11-BL
ZDK2.5-11-PE
ZDK2.5-21
ZDK2.5-22
ZDK2.5-22-BL
ZDK2.5-22-PE
ZDK2.5-D1
ZDK2.5-D1-PE
ZDK2.5-D2

INDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONS

Index_1SNC160034C0201

Index
Type classification

IndexType classification
Part Number

Page

Type

Part Number

Page

ZS4-D2-BL
ZS4-D2-OR
ZS4-D2-S
ZS4-D2-SF1
ZS4-D2-SF1-R1
ZS4-D2-SF1-R3
ZS4-D2-S-T2
ZS4-D-CH-DU
ZS4-D-CH-UD
ZS4-GNZS4-ORZS4-PEZS4-PE-R2
ZS4-PRZS4-R1ZS4-R2ZS4-RDZS4-S
ZS4-S-BLZS4-SFZS4-SF1ZS4-SF1-OR
ZS4-SF1-R1
ZS4-SF1-R2
ZS4-SF1-R3
ZS4-SF1-R4
ZS4-SF1-T2
ZS4-SF-R1
ZS4-SF-R2
ZS4-SF-R3
ZS4-SF-R4ZS4-SF-T2
ZS4-S-ORZS4-SPZS4-SP-R1
ZS4-SP-T2
ZS4-SP-T2-R1
ZS4-S-R1
ZS4-S-R1-BL
ZS4-S-R1-OR
ZS4-S-R2ZS4-S-R3ZS4-S-R3-T2
ZS4-S-T2ZS4-S-T2.3
ZS4-S-T2.3-R1
ZS4-S-T2-BL
ZS4-S-T2-OR
ZS4-S-T2-R1
ZS4-S-T2-R1-BL
ZS4-S-T2-R1-OR
ZS4-T3ZS4-T3-R1
ZS4-WHZS4-YL
ZS50
ZS50-BK
ZS50-BL
ZS50-PE
ZS50-RD
ZS50-YL
ZS6
ZS6-3S
ZS6-3S-BL
ZS6-3S-PE
ZS6-3S-YL
ZS6-4S
ZS6-4S-BL
ZS6-4S-PE
ZS6-4S-YL
ZS6-BKZS6-BLZS6-BRZS6-D1ZS6-D1-PE
ZS6-D1-RD
ZS6-D2

1SNK505220R0000
1SNK505230R0000
1SNK505315R0000
1SNK508425R0000
1SNK508423R0000
1SNK508424R0000
1SNK505316R0000
1SNK505215R0000
1SNK505214R0000
1SNK505061R0000
1SNK505030R0000
1SNK505150R0000
1SNK506153R0000
1SNK505063R0000
1SNK508013R0000
1SNK506013R0000
1SNK505062R0000
1SNK505310R0000
1SNK505320R0000
1SNK506410R0000
1SNK508410R0000
1SNK508430R0000
1SNK508412R0000
1SNK508413R0000
1SNK508414R0000
1SNK508415R0000
1SNK508411R0000
1SNK506412R0000
1SNK506413R0000
1SNK506415R0000
1SNK506416R0000
1SNK506411R0000
1SNK505330R0000
1SNK505313R0000
1SNK506313R0000
1SNK505314R0000
1SNK506314R0000
1SNK506310R0000
1SNK506320R0000
1SNK506330R0000
1SNK506414R0000
1SNK508416R0000
1SNK508419R0000
1SNK505311R0000
1SNK505312R0000
1SNK506312R0000
1SNK505321R0000
1SNK505331R0000
1SNK506311R0000
1SNK506321R0000
1SNK506331R0000
1SNK505212R0000
1SNK506213R0000
1SNK505065R0000
1SNK505060R0000
1SNK516011R0000
1SNK516064R0000
1SNK516021R0000
1SNK516151R0000
1SNK516063R0000
1SNK516060R0000
1SNK506010R0000
1SNK506011R0000
1SNK506021R0000
1SNK506151R0000
1SNK506067R0000
1SNK506012R0000
1SNK506022R0000
1SNK506152R0000
1SNK506068R0000
1SNK506066R0000
1SNK506020R0000
1SNK506064R0000
1SNK506211R0000
1SNK506250R0000
1SNK506214R0000
1SNK506210R0000

284
284
290
292
293
293
291
297
296
228
228
228
279
228
272
278
228
253
253
274
268
268
270
271
270
271
269
276
277
276
277
275
253
260
262
261
263
255
255
255
280
273
273
254
254
256
254
254
256
256
256
294
295
228
228
236
236
236
236
236
236
229
230
230
230
230
231
231
231
231
229
229
229
287
286
287
286

ZS6-D2-BK
ZS6-D2-BL
ZS6-D2-OR
ZS6-D2-PE
ZS6-D2-RD
ZS6-D2-WH
ZS6-D2-YL
ZS6-GNZS6-ORZS6-PEZS6-PRZS6-RDZS6-S
ZS6-S-4S-T2
ZS6-S-BL
ZS6-WHZS6-YL
ZS70
ZS70-BL
ZS70-PE
ZS70-YL
ZS95
ZS95-BL
ZS95-PE
ZS95-YL

1SNK506266R0000
1SNK506220R0000
1SNK506230R0000
1SNK506212R0000
1SNK506262R0000
1SNK506265R0000
1SNK506260R0000
1SNK506061R0000
1SNK506030R0000
1SNK506150R0000
1SNK506063R0000
1SNK506062R0000
1SNK506315R0000
1SNK506316R0000
1SNK506322R0000
1SNK506065R0000
1SNK506060R0000
1SNK522010R0000
1SNK522020R0000
1SNK522150R0000
1SNK522060R0000
1SNK526010R0000
1SNK526020R0000
1SNK526150R0000
1SNK526060R0000

286
286
286
288
286
286
286
229
229
229
229
229
257
258
257
229
229
237
237
237
237
238
238
238
238

Type

Part Number

Page

Index_1SNC160034C0201

Type

PAGE 359

10

NotesINDUSTRIAL /// ENTRELEC - RAILWAY APPLICATIONSMARKING SOLUTIONSMarkers & marking systems
ENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSPB2TE Connectivity proposes a large scope of solutions
for all identification requirements within theelectrical panel.
Identify all your equipment through our comprehensive
range of markers, labels for terminal block,wire & cable, component & equipment...
Find your favorite marking solution from budget
sensitive printing jobs to high quality & volume projects.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSMarking solutions

Markers and marking systems
2

1

HTP500 thermal transfer printer and compatible markers

92

MG3 thermal transfer printer and compatible markers

373

AMS 600 and AMS 250 plotter and compatible markers

754Pre-printed and customized markers

111

5

Other manufacturers' terminal block markers selection guides

158

6

Index

170

7

Summary_1

Overview

1-1773967-4_EN - Edition July 2019

PAGE 1

ENTRELEC Terminal blocks

TE Connectivity proposes one of the largest Din Rail Terminal block offering on themarket with various technologies: screw, PI-Spring, spring, IDC, pluggable, stud, etc.
found in over 8000 products & solutions.

1

Scope

SNK
terminal blocks

Dedicated applications
terminal blocks

Terminal blocks forrailway applications

Qualified for worldwide applications andsevere environments (such as hazardous
locations, railways, marine and solar
applications..).
From 0.2 to 300 mm².

Specific terminal blocks and technologies
for dedicated applications and markets.

The largest offering on
the market for rollingstock and infrastructures.

Product
SNK PI-Springfamilies & technology
functions 2.5 to 16 mm²
12 to 4 AWG

Feed-throughMulti-deck
GroundDisconnect
for fuses
Component holder

ADO System® (IDC)
0.22 to 4 mm²
24 to 12 AWG

ADO-ADO or ADO-screw clamp SNK PI-Spring technology
Feed-through / Multi-deck /2.5 to 16 mm²Ground / Disconnect /12 to 4 AWG
for fuses / Component holder

Safety (spring loaded)
0.22 to 10 mm²
24 to 6 AWG

Feed-throughDisconnect
Test & measurement

SNK pluggablescrew & PI-Spring technologies
2.5 to 4 mm²
12 to 10 AWG

SNK screw clamp
technology
4 to 240 mm²
12 to 500 Kcmil

Feed-throughMulti-deck
GroundDisconnect
for fuses
Test & measurement
Marshalling
Component holderStud
25 to 300 mm²
4 AWG to 1000 Kcmil

One stud
2 studs
One stud - One screw clamp

ADO System® (IDC)
1.5 to 4 mm²
16 to 12 AWG

Ring lug
6 to 16 mm²
8 to 6 AWG

Feed-throughTest & measurementStud
4 to 185 mm²

SNK pluggablescrew & PI-Spring
technologies
2.5 to 4 mm²
12 to 10 AWG

Feed-throughMulti-deck
GroundMiniblocks
1.5 to 6 mm²
18 to 8 AWG

Screw clamp
SpringADO System ® (IDC)

Quick-connect
2.5 to 6 mm²

Other types
Test & measurement: with sliding link, blade, plug
Pluggable: feed-through, double deck, disconnect
Sensors/actuators: screw, spring, ADO system (IDC)
Installation: screw, spring
Protection: ground + neutral
Component holders: screw, spring, ADO system (IDC)

www.te.com

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSDBL power
distribution blocks

ESSAILEC®
test blocks

Interfast PLC
pre-wiring system

Marking
solutions

The preferred choice for primary
power distribution and solar
applications.

Test blocks for safe and easy
testing on secondary circuitsof current and voltage
transformers and sensors.

PLC pre-wiring system for fast,
flexible, reliable connection of PLC’sin process automation applications.

Markers & marking systems for
all identification requirements inelectrical panels.

From 80 A up to 550 A (IEC)

Current and voltage
sockets & plugs

Interfast PCB:
Compact & standard modules

Terminal block identification andgroup markers

Simultaneous testing of
1 to 4 independent circuitson the same socket

Interfast MS:
Modular system based onterminal block technology

Wire and cable identification

Terminal blocks types:
2 to 10 poles, up to 20 outputs

Component and equipment
identification

Several testing principle such
Functions:as “make before break” for safe – – 1 to 4 wire connections (sensors) Panel identification
current transformer testing– – Disconnect
Pre-printed markers for terminal– – Fuse
blocksPanel and switchboard
mounting : base, flush, rack,– – Signal indication
TH35 rail– – Relays
Multicircuits sockets & plugs– – Optocouplers– – Solenoid valve control– – Galvanic isolation (2.5 kV).

1SNC160261S0201

Modular blocks: single pole, three& four poles, up to 12 outputs

1

PAGE 3

Marking solutions
Comprehensive range for all identification requirements

1

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

Panel identification
1

Terminal block identificationand group markers

Wire and cable identification

1SNC160206S0201

Component and equipment
identification

PAGE 5

Marking systems
Selection guide

For versatile applications

1

Marking systems

MG3

Technology

Thermal transfer

Printing mode

ManualPrinting speed

MediumPrinting quality

300 x 600 dpi

1 ribbon or ink cartridge printing capacity~ 160 000, MG-CPM (5 x 10 mm markers)

Printing color available (monochrome)

Black / Red / Blue / Green / White

Terminal block markers material

Polycarbonate

Terminal block markers
SNK series terminal blocks blank markers polyamide–

SNK series terminal blocks blank markers polycarbonate

MG-CPM

SNK series terminal blocks blank markers PVC

MG-CPMF

SNA and solution series terminal blocks blank markers polyamide–

SNA and solution series terminal blocks blank markers polycarbonate MG-CPM
SNA and solution series terminal blocks blank markers PVC

MG-CPMF

SNA and solution series terminal blocks blank side markers(5 mm height) polyamide–

End stop markers

2 marker types

Other terminal blocks manufacturers blank markers

15 manufacturers

Wires and cables markers

4 marker types

Components and equipment markers

9 marker types

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSFor basic marking applications

1

AMS 600 - AMS 250
PlotterManualLow
300 x 300 dpi~ 230 000 markers (with 3 characters per markers)
Black
Polyamide

MC…PA
–
–
RC / RCAL / RB / RCT / RCP5 / RPEV–
REH / RTM
RC55 / RC65
4 marker types
5 manufacturers
1 marker type

1SNC160207S0201

9 marker types

PAGE 7

Summary_2

2

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSMarking solutions
Blank markers and labels for HTP500 thermal transfer printer

HTP500 kit and accessories

10

Terminal block identification
Selection guide for terminal block markers
Terminal block markers

12
MC…

for SNK series

14

RC…TT

for SNA and Solution series

15
16

Other manufacturers' terminal block markers

RCP, RCW, RCL

End stop markers

MCLH, MCLH-R1

for SNK series

18

RCPEAD-TT

for SNA and Solution series

20

End stop label holders and covers

LH, LH-R1

for SNK series

19

PEAD, EPR2

for SNA and Solution series

20

PEB, PEBM, EPR1

for SNA and Solution series

29

Wire and cable markers

WMTT

PVC label (need label holder)

24

PCGS

large label (need label holder)26

Wire and cables label holders

RING, SNAP, RINGT23

transparent label holder

25

RINGT209

for large label tied-on thick cables

26

PAM

for strip identification30

Pre-cut labels

BA4

for contactors, relays...

31

PPB

two-colored label

32

Label holders and covers

PAM100015, PCT

15 mm rail and protective cover33

KA1-8120

push-button marker holder

33

2Wire and cable identification
Selection guide for wire and cable markers

22			

Component and equipment identification
Self-adhesive labels

28

RPA-TT, PIB2-TT		

Panel identification
Self-adhesive panel plates

PAT

34

Rivet fixing panel plates

PPT

34

158

Summary_2

Other manufacturers markers selection guide		

PAGE 9

HTP500 thermal transfer printerKit and accessories
Description–– Performance,–– High volume and serial production,–– Dedicated to terminal blocks.
HTP500-V2 KIT

2HTP500-CLEAN

Ordering details
Description
Thermal transfer printer KIT
List of items included in the KIT :1 HTP500-V2 Thermal transfer printer
1 software CD
1 power supply cable
1 USB cable
1 support table
1 universal feeder for marker cards
1 cleaning cassette
1 black ribbon cassette
1 support plate for terminal block markers
1 universal support plate for wire markers

Type
HTP500-V2 KIT

Pkg

Part Number
1SNA235700R1500

Weightpce(1 pce) g

116000.00

HTP500-V2
HTS500
HTP500-PW
HTP500-USB
HTP500-BAS
HTP500-FEED
HTP500-CLEAN
RIB-B
HTP500-PL2
HTP500-PL

Feeders and support plates
Description

HTP500-FEED

Universal feeder for marker cards
Support plate for terminal block markers
Universal support plate for wire markers
Support plate for other manufacturers terminal block markers
Support plate for BA4 markers

TypePart Number

Pkg

Weightpce(1 pce) g

515.00130.00294.00130.00291.00

HTP500-FEED
HTP500-PL2
HTP500-PL
HTP500-PL3
HTP500-BA4

1SNA235703R0400
1SNA235705R0600
1SNA235704R0500
1SNA235707R0000
1SNA235712R2400

1
1
1
1
1

Type

Part Number

Pkg

Accessories
Description
HTP500-PL

HTP500-PL2

HTP500-PL3Black ribbon cassette
Red ribbon cassette for identification plates and adhesive labels
Red ribbon cassette for terminal blocks and wire markers
Cleaning cassetteStandard cleaning roll ø18
Printing head
Power supply cable
Dust cover for HTP500 and AMS 500 systems
Wooden box for HTP500-V2 KIT
Software CD
Support table
Power supply cable

RIB-B
RIB-R
RIB-RS
HTP500-CLEAN
HTP500-ROLL
HTP500-PRINT
HTP500-PW
DUST COVER
HTP500-WB
HTS500
HTP500-BAS
HTP500-PW

1SNA235710R0600
1SNA235711R2300
1SNA235718R0200
1SNA235714R2600
1SNA235715R2700
1SNA235716R2000
1SNA235709R1200
1SNA360161R1500
1SNA235717R2100
1SNA235702R0300
1SNA235706R0700
1SNA235709R1200

Weightpce(1 pce) g

3
3
3
1
1
1
1
1
1
1
1
1

69.03
69.03
69.03
83.50
40.50
20.00
120.00200.009980.00
17.00
4060.00
120.00

1SNK160084S0201

RIB-B

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

PB13

2

PAGE 11

HTP500 markers selection guide
Terminal block blank markers selection guide
Terminal blocks (Terminal blocks styles not listed on the chart do not have a marker compatible with this printer)2

Connection technology

Terminal block part number

Marker typeMarker mounting

Screw clamp

1SNK...

Strip marker

Top and side marking

1SNA... (1)Strip marker

Side marking

PI-Spring andpluggable
PI‑Spring

1SNK...

Strip marker

Top and side marking

Spring clamp

1SNA... (1)Strip marker

Top marking

Spring loaded
screw clamp

1SNA...

Strip marker

Side marking

Pluggablescrew clamp

1SNA...

Strip marker

Side marking(1) Except mini-blocks.

SNK series end stop and label holders
BAZ1

Individual
marker

BAM4
LH (label holder for BAM4, BAZH1, BAZ1)

Label

LH-R1 (label holder for BAM4, BAZH1, BAZ1)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

Top marking

MC512

Top and sidemarking

MC812

Top marking

MC-LH
MC-LHR1

Terminal blocks spacing
5 mm
5.08 mm
5.2 mm0.197 in
0.200 in
0.205 in
MC512

RC510TT

MC512

6 mm
0.236 in

8 mm
0.315 in

MC612

MC812

RC610TT

RC810TT

MC612

MC812

10 mm
0.394 in

12 mm
0.472 in

16 mm
0.630 in

22 mm
0.866 in

26 mm
1.024 in

31 mm
1.220 in

36 mm
1.417 in

MC812 (2)RC810TT (2)MC812 (2)2RC510TT

RC610TT

RC810TT

RC610TT

RC810TT

RC810TT (2)RC810TT (2)RC510TT(2) Marker width < marking's area size - markers must be mounted individually.

SNA series end stop and label holders
BAM2, BADH

Individual
markerTop and sidemarking

RC810TTBADLBADRL, BAR

RC810TT (2)Individual
marker

Top marking

RC610TT
RC810TT

BAMH
PEAD (Label holder for BAM2 and BADL)Label

Top marking

RCPEAD-TT

PEB

Label

Top marking

PIB2-TT

1SNC160209S0201 - Rev. A(2) Marker width < marking's area size - markers must be mounted individually.

PAGE 13

1SNK160156F0014

MC terminal block markers
Blank markers for SNK series

MC512

Description–– Blank marker card designed for high marking quality,–– Dedicated to SNK series terminal block marking,–– Excellent marking durability in the most severe environments,–– Made of rigid polycarbonate.

Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

1SNK140000R0000
1SNK140004R0000

22
22

9.00
9.00

1SNK150000R0000
1SNK150004R0000

22
22

10.00
10.00

1SNK160000R0000
1SNK160004R0000

22
22

10.00
10.00

1SNA235705R0600

1

291.00

SNK series terminal block markers
MC512
For 5.2 mm 0.205 in spacing terminal blocks and BAZ1 end stop
12 x 50.472 x 0.197 3
8
45
White
MC512
Yellow
MC512-YL
MC612
For 6 mm 0.236 in spacing terminal blocks
12 x 5.6 0.472 x 0.220 3
8
39

White
Yellow

MC612
MC612-YL

MC812
For 8 mm 0.315 in and larger spacing terminal blocks and BAM4 end stop
12 x 7.6 0.472 x 0.299 4
8
30
White
MC812
Yellow
MC812-YL

Marking System Accessories
HTP500-PL2
Support plate
Included in the HTP500-V2 kit

HTP500-PL2

Mounting instruction

1SNC160190S0201

2

Maximum
printed digits
Hor.
Vert.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC..TT terminal block markers
Blank markers for SNA and Solution series

RC510TT–– Blank marker card designed for high marking quality,–– Excellent marking durability in the most severe environments,–– Made of rigid polycarbonate.

Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-50°C to +120°C -58°F to +248°F

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

For 5 mm 0.197 in terminal block spacing

2

RC510TTFor 5 mm 0.197 in spacing terminal blocks
10 x 50.394 x 0.197 3
7
48

White
Yellow

RC510TT
RC510TT-YL

1SNA231600R1500
1SNA231700R1100

22
22

12.00
12.00

RC610TT
RC610TT-YL

1SNA233600R1700
1SNA233700R1300

22
22

12.00
12.00

For 8 mm 0.315 in and larger spacing terminal blocks and end stops from SNA series
10 x 80.394 x 0.315 4
7
30
White
RC810TT
1SNA234600R1000
Yellow
RC810TT-YL
1SNA234700R1400

22
22

12.00
12.00

1

291.00For 6 mm 0.236 in terminal block spacing
RC610TTFor 6 mm 0.236 in spacing terminal blocks
10 x 6
0.394 x 0.236 3
7
39

White
Yellow

For 8 mm 0.315 in terminal block spacing
RC810TT

Marking System Accessories
HTP500-PL2
Support plate
Included in the HTP500-V2 kit

HTP500-PL2

1SNA235705R0600

Mounting instruction

1SNC160191S0201

1SNC160246F0014

Description

PAGE 15

RCP, RCW, RCL terminal block markers
Blank markers for other manufacturers

1SNC160249F0014

Description–– Blank marker card designed for high marking quality,–– To be used to mark terminal blocks from other manufacturers,–– Excellent marking durability in the most severe environments,–– Made of rigid polycarbonate.

RCP510Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-50°C to +120°C -58°F to +248°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

RCP510For Wago and Phoenix screw clamp terminal blocks
10 x 50.394 x 0.197 3
7
45
White

RCP510

1SNA235095R1600

12

11.25

White

RCW510

1SNA235096R1700

12

10.83

For Legrand, Wieland and Télémécanique terminal blocks
10 x 50.394 x 0.197 3
7
45
White

RCL510

1SNA235097R1000

12

10.42

HTP500-PL3

1SNA235707R0000

1

130.00RCW510For Weidmüller terminal blocks
10 x 50.394 x 0.197 3
745

RCL510Marking System Accessories
HTP500-PL3
Support plate
Purchased separately

See other manufacturer selection guide at the end of this catalogue.

1SNC160192S0201

2

Maximum
printed digits
Hor.
Vert.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

PB19

2

PAGE 17

MCLH end stop markers
Self-adhesive precut blank labels for SNK series

1SNC700301F0000

Description

MCLH, MCLH-R1–– Identify your terminal block assemblies with the self-adhesive label adapted to the LH label holders.

Main technical data
Material
PVC + Adhesive acrylic

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensionsmm

Nb. ofmarkers
per card

in

Color

Type

Part Number

Pkg

Weightcard(1 card) g

For LH label holder
MCLH
30 x 8.8

1.181 x 0.346

36

White
Yellow

MCLH
MCLH-YL

1SNK900630R0000
1SNK900633R0000

25
25

10.00
10.00

White
Yellow

MCLH-R1
MCLH-R1-YL

1SNK900631R0000
1SNK900634R0000

25
25

10.00
10.00

For LH-R1 label holder
MCLH-R1
35.35 x 17.65

1.392 x 0.695

15Marking system accessories
No support plate needed.
Direct insertion into HTP500 marking system for printing.

Mounting instruction

MCLH

8.8
0.346"

30 1.18"

MCLH-R1

17.65 0.695"

35.35 1.39"

Compatible holders

LH

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

LH-R1

1SNC160200S0201

2

LH, LH-R1 end stop label holders
For MCLH labels
Description

1SNK160210F0014–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Main technical data
Material
Polyamide

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Spacingmm

Dimensions
in

mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

For MCLH
LH
10

0.35 x 1.18

Dark GreyLH

1SNK900605R0000

50

0.60

17.9 x 35.65 0.70 x 1.40

Dark Grey

LH-R1

1SNK900607R0000

50

1.10

For MCLH-R1
LH-R1
19.5
0.768

LH-R1

8.8 x 30

Dimensions given apply to the labelling area.

Compatible end stops

BAM4
1SNK900001R0000

BAZ1
1SNK900002R0000

1SNC160201S0201

LH

0.394

2

BAZH1
1SNK900102R0000

PAGE 19

RCPEAD-TT end stop labels
Self-adhesive precut blank labels

1SNC700302F0000

Description

RCPEAD-TT–– Identify your terminal block assemblies with the self-adhesive label adapted to the PEAD label holders.

Main technical data
Material
PVC + Adhesive acrylic

Flammability
V0

Ordering details
Dimensionsmm

Nb. ofmarkers
per cardin

RCPEAD-TT
9 x 290.354 x 1.142

Color

36

Type

White
Yellow

RCPEAD-TT
RCPEAD-TT-YLPart Number

1SNA235158R0100
1SNA235159R0200

Pkg

Weightcard(1 card) g

25
25

9.80
9.60

Marking system accessories

2

No support plate needed.
Direct insertion into HTP500 marking system for printing.

Mounting instruction
PEAD + RCPEAD-TT

PEAD end stop label holders
For RCPEAD label
Description–– Easily identify your terminal block assemblies with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with BAM2 and BADL SNA series end stops.

1SNC160058F0014

Main technical data

PEAD

Material
Polyamide

Flammability
V0

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

20

0.78

1

4.00

PEAD
Label holder for end stop, compatible with RCPEAD and RCEPAD-TT markers and EPR2 cover.
9 x 290.354 x 1.142
Grey
PEAD
1SNA399719R1000
Dimensions given apply to the labelling area.

EPR2
Card of 20 covers for RCPEAD and RCPEAD-TT markers
9 x 290.354 x 1.142
Transparent

EPR2

1SNA399726R0700

BAM2
1SNA206351R1600

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSBADL
1SNA399903R0200

1SNC160202S0201 - Rev. A

Compatible end stops

PB23

2

PAGE 21

HTP500 wire and cable markers
Selection guide
Evolutive and protected wire andcable identification
Each individual label and label holder iseasily detached from the stem for installation onto cable. The printed label in its
holder is perfectly protected over time.

2

SNAP
Clip-on cable label holders tobe snap-on the wire alreadyconnected or not.

RINGT
Tie-on cable label holders
recommended for thick tube,
hose and conduit.

1SNC160210S0201

RING
Slide-on cable label holders
to be used before connecting
the wires.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSHTP500 wires and cables markers
Selection guide

For evolutive identification
Marker holders + slide-in markers

Wire external diameter
mm
in

RING

SNAP

Marker holder lengthmminMarker holder

Compatible marker

Slide-on cable marker holder
Ø 1.5 ... 2.5
Ø 0.059 ... 0.098
1218
Ø 2 ... 4
Ø 0.079 ... 0.157
1218
Ø 4 ... 7
Ø 0.157 ... 0.276
1218
Ø 6 ... 10Ø 0.236 ... 0.394
12
18

0.472
0.709
0.472
0.709
0.472
0.709
0.472
0.709

RING122
RING182
RING124
RING184
RING127
RING187
RING1210
RING1810

WMTT 12
WMTT 18
WMTT 12
WMTT 18
WMTT 12
WMTT 18
WMTT 12
WMTT 18

Clip-on cable marker holder
Ø 2 ... 3.5
Ø 0.079 ... 0.138
15
23
Ø 2.8 ... 5Ø 0.11 ... 0.197
1523
Ø 5 ... 8
Ø 0.197 ... 0.315
1523
Ø 8 ... 10Ø 0.315 ... 0.394
15
23

0.591
0.906
0.591
0.906
0.591
0.906
0.591
0.906

SNAP152
SNAP232
SNAP154
SNAP234
SNAP157
SNAP237
SNAP1510
SNAP2310

WMTT 12
WMTT 18
WMTT 12
WMTT 18
WMTT 12
WMTT 18
WMTT 12
WMTT 182

For identification of thick tubes
Tie-on markers / marker holders

RINGT23

Marker holder length
mm
in
23
23
28
28

Marker holder

Compatible marker

RINGT23
RINGT209

WMTT 18
PCGS209

1SNC160210S0201

RINGT209

PAGE 23

WMTT wire and cable markers
Slide-in precut blank labels

1SNC700183F0000

Description–– Blank marker card for wire and cable identification,–– Markers are protected in the marker holders,–– To be slided into RING or SNAP transparent holders,–– Made of rigid polycarbonate.

WMTT12Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-50°C to +80°C -58°F to +176°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

WMTT1212 mm 0.472 in markers (for RING or SNAP holders)
12 x 40.472 x 0.157 2
8
30
White

WMTT12

1SNA235093R1400

32

6.70

WMTT18

1SNA235094R1500

32

7.00

HTP500-PL

1SNA235704R0500

1

294.00

WMTT1818 mm 0.709 in markers
18 x 40.709 x 0.157 2

10

18

White

Marking system accessories
HTP500-PL
Support plate
Included in the HTP500-V2 kit

Compatible holders

RING
Sealed transparent holder

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

SNAPUnsealed transparent holder

RINGT23
Tie-on sealed transparent holder

1SNC160193S0201

2

Maximum
printed digits
Hor.
Vert.

RING, SNAP transparent marker holders
For WMTT markers
Description
1SNC160251F0014–– Transparent marker holder profiled to allow marking on various cable sizes, up to ø 10 mm 0.394 in,–– Use with WM and WMTT markers,–– Made of PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-50°C to +80°C -58°F to +176°F

Ordering details
Wire ext. diameter
mm

in

Wire
sectionmm²

Holder length
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

For cable mounting

2

RING

RING

12 mm 0.472 in sealed transparent holder for WM12 and WMTT12 markers
1.5 ... 2.5 0.059 ... 0.098
12
0.472Transparent
RING122
2 ... 40.079 ... 0.157
Transparent
RING124
4 ... 70.157 ... 0.276
Transparent
RING127
6 ... 100.236 ... 0.394
Transparent
RING1210
18 mm 0.709 in sealed transparent holder for WM18 and WMTT18 markers
1.5 ... 2.5 0.059 ... 0.098
18
0.709
Transparent
RING182
2 ... 40.079 ... 0.157
Transparent
RING184
4 ... 70.157 ... 0.276
Transparent
RING187
6 ... 100.236 ... 0.394
Transparent
RING1810

1SNA235117R1000
1SNA235118R2100
1SNA235119R2200
1SNA235120R2700

3000
3000
2000
2000

1.80
2.20
0.30
0.50

1SNA235123R1600
1SNA235124R1700
1SNA235125R1000
1SNA235126R1100

3000
3000
2000
1000

0.30
0.30
0.50
0.70

1SNA235129R2400
1SNA235130R2100
1SNA235131R1600
1SNA235132R1700

1000
1000
500
500

0.40
0.40
0.50
1.40

1SNA235133R1000
1SNA235134R1100
1SNA235135R1200
1SNA235136R1300

500
500
200
200

0.40
0.60
0.90
2.20

1SNA235137R1400

200

0.40

SNAP

SNAP

12 mm 0.472 in un-sealed transparent holder for WM12 and WMTT12 markers
2 ... 3.5
0.079 ... 0.138
15
0.591
Transparent
SNAP152
2.8 ... 50.110 ... 0.197
Transparent
SNAP154
5 ... 80.197 ... 0.315
Transparent
SNAP157
8 ... 100.315 ... 0.394
Transparent
SNAP1510
23 mm 0.906 in in un-sealed transparent holder for WM18 and WMTT18 markers
2 ... 3.5
0.079 ... 0.138
23
0.906
Transparent
SNAP232
2.8 ... 50.110 ... 0.197
Transparent
SNAP234
5 ... 80.197 ... 0.315
Transparent
SNAP237
8 ... 100.315 ... 0.394
Transparent
SNAP2310

For thick tube mounting
RINGT23
23 mm 0.906 in tie-on sealed transparent holder for WM and WMTT markers
23
0.906
Transparent
RINGT23

1SNC160194S0201

RINGT23

Use holders only with designated cable marker of the same or a shorter length.

PAGE 25

PCGS wire and cable markers
Slide-in precut blank labels

1SNC700181F0000

Description

PCGS209–– Blank marker card for thick wires,–– To be inserted in RINGT209 holder,–– Made of PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +60°C -40°F to +140°F

Ordering details
Dimensionsmm

Nb. ofmarkers
per card

in

Color

Type

Part Number

Pkg

Weightcard(1 card) g

PCGS

2

For RINGT holders
20 x 9.3
0.787 x 0.366

60

White

PCGS209

1SNA235150R0500

40

10.00

HTP500-PL

1SNA235704R0500

1

294.00Pkg

Weightpce(1 pce) g

240

6.00

Marking system accessories
HTP500-PL
Support plate
Included in the HTP500-V2 kit

RINGT209 transparent marker holders
For PCGS markers

1SNC160100F0014

Description

RINGT209–– Transparent tie-on marker holders profiled to allow thick tube identification,–– Use with PCGS209 markers,–– Made of PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-50°C to +80°C -58°F to +176°F

Ordering details
Dimensions
mm

Color

Type

Part Numberin

For thick tube mounting
RINGT209
Tie-on sealed transparent holder for PCGS markers
9.5 x 200.374 x 0.787
Transparent

RINGT209

1SNA235142R2100

1SNC160195S0201

Use holders only with designated cable marker of the same or a shorter length.
Dimensions given apply to the labelling area.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

PB29

2

PAGE 27

RPA-TT, PIB2-TT component and equipment markers
Self-adhesive precut blank labels

1SNC160253F0014

Description

RPA-TT–– Self-adhesive labels for general purpose,–– High performance adhesive compatible with most surface types.

Main technical data
Material
PVC + Adhesive acrylic

Flammability
V0

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

RPA-TT
Card of 77 self-adhesive blank labels
8 x 17.5
0.315 x 0.689
77

White
Yellow

RPA-TT
RPA-TT-YL

1SNA235151R2200
1SNA235152R2300

25
25

12.50
12.10

White
Yellow

PIB2-TT
PIB2-TT-YL

1SNA235155R2600
1SNA235157R2000

25
25

9.70
9.40

PIB2-TT
Card of 15 self-adhesive blank labels
35 x 17.5 1.392 x 0.689
15Marking system accessories
No support plate needed.
Direct insertion into HTP500 marking system for printing.

Mounting instruction

Compatible holders

PEB(only for PIB2-TT)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160203S0201

2

PEB end stop label holders
For PIB2-TT labels
Description

PEB

Main technical data
Material
Polyamide (PEB)
PVC (EPR1)

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

50

1.70

PEB
Label holder for end stop 35 x 17 mm 1.378 x .669 in, to be snapped onto end stop
18 x 35.5
0.709 x 1.378
GreyPEB
1SNA113077R1100

2

EPR1
Card of 54 PVC protective covers
17.5 x 35
0.689 x 1.378

Transparent

EPR1

1SNA178431R2200

1

0.054

"All in one": PEB marker holder with marker and protection included
PEBM

1SNA113084R0100

50

2.80

BAR
1SNA164519R2400

BADRL
1SNA199420R2100

PEBM

Compatible end stops

BAM2
1SNA206351R1600

BADL
1SNA399903R0200

BADH
1SNA116900R2700

BAMH
1SNA114836R0000

PAGE 29

1SNC160204S0201 - Rev. A

1SNC160200F0014–– To be used for terminal block assembly identification,–– Direct insertion onto end stops from SNA series.

PAM component and equipment markers
Self-adhesive precut blank labels

1SNC700197F0000

Description

PAM–– Self-adhesive blank labels used to identified different components and equipments in a cabinet,–– Can be used directly on equipment or with a label holder.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +60°C -40°F to +140°F

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

20
20

12.00
22.00

20
20

14.00
27.00

PAM
Self-adhesive blank label compatible with PAM100015 and PCT100015 transparent cover
15 x 215
0.591 x 8.465
2
White
PAM21515
1SNA235103R2300
15 x 430
0.591 x 16.930
White
PAM43015
1SNA235104R2400
Self-adhesive blank label
20 x 215
0.787 x 8.465
2
White
PAM21520
1SNA235105R2500
20 x 430
0.787 x 16.930
White
PAM43020
1SNA235106R2600

Marking system accessories
No support plate needed.
Direct insertion into HTP500 marking system for printing.

Compatible holders
PCT100015

PAM100015

Protective cover and self-adhesive marking profile(only for PAM21515 and PAM43015)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160196S0201

2

BA4 component and equipment markers
Precut blank label–– Precut blank label used to identify contactors, overload relays and manual motor starters,–– Compatible with: AF09 ... AF370 contactors, TF thermal overload relays, EF electronic overload relays, andMS116, MS132 manual motor starters.

Main technical data
Material
Polycarbonate

Flammability
V0

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightcard(1 card) g

BA4
Card of 16 blank labels
7 x 200.276 x 0.787

2

White

BA4

1SNA235156R2700

16

11.00

HTP500-BA4

1SNA235712R2400

1

290.00Marking system accessories
HTP500-BA4
Support plate for AMS600
Purchased separately

Mounting instruction

1SNC160205S0201 - Rev. B

1SNC160101F0014

Description

PAGE 31PPB component and equipment markers
Two-colored precut blank labels

1SNC700200F0000

Description

PPB–– Two-colored blank label cards, white side / black side,–– For push button or sub-assembly identification,–– To be used with a label holder.

Main technical data
Material
MMA

Flammability
HB

Temperature range-40°C to +82°C -40°F to +180°F

Ordering details
Dimensions
inPPB
15 x 270.591 x 1.063

16

Color

White and BlackType

PPB2715

Part Number

1SNA235111R1200

Pkg

Weightcard(1 card) g

12

13.30

Marking system accessories
No support plate needed.
Direct insertion into HTP500 marking system for printing.

Compatible holders
PCT100015

PAM100015

Protective cover and self-adhesive marking profile

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

KA1-8120
Push button marker holder

1SNC160197S0201

2mm

Nb. ofmarkers
per card

PAM100015, PCT, KA marker holders
For PAM21515, PAM43015 and PPB labels
Description

1SNC160268F0014–– For component and equipment identification,–– Self-adhesive marking profile (PAM), transparent cover (PCT) and push-button marker holder (KA1).

Main technical data
Material
PVC (for PAM and PCT)
Polycarbonate (for KA1)

Flammability
V0 (for PAM and PCT)
V2 (for KA1)

Temperature range-10°C to +70°C +14°F to +158°F (for PAM
and PCT)-25°C to +70°C -13°F to +158°F (for KA1)

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

2

Push-button marker holder
KA1
Push button marker holder for PPB markers
15 x 270.591 x 1.063
KA1-8120

Black

KA1-8120

1SFA616920R8120

10

2.00

Self-adhesive marking profile for PAM and PPB markers
PCT

PCT100015

Transparent cover for PAM100015
15 x 1000
0.591 x 39.370

Transparent

PCT100015

1SNA235147R2600

35

34.00

Black

PAM100015

1SNA235146R2500

35

40.00

PAM100015
Adhesive marking profile
15 x 1000
0.591 x 39.370
Dimensions given apply to the labelling area.

1SNC160198S0201

PAM100015

PAGE 33

PAT panel plates
Self-adhesive blank panel plates

1SNC700214F0000

Description

PAT–– Self-adhesive blank plate for identification of electrical boxes or cabinets.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +120°C -40°F to +248°F

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

15

5.30

Pkg

Weightpce(1 pce) g

50
30

3.50
8.80

PAT
Adhesive plate for external marking
60 x 100
2.262 x 3.937
1

2

White

PAT10060

1SNA235114R1500

Marking system accessories
No support plate needed.
Direct insertion into HTP500 marking system for printing.

PPT panel plates
Blank panel plates

1SNC700213F0000

Description

PPT–– Blank perforated plate for identification of electrical boxes or cabinets,–– To be fixed with rivets.

Main technical data
Material
MMA

Flammability
HB

Temperature range-40°C to +82°C -40°F to +180°F

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

PPT
Perforated blank plate
30 x 1201.181 x 4.724
50 x 180
1.969 x 7.087

1

White
White

PPT12030
PPT18050

1SNA235115R1600
1SNA235116R1700

Marking system accessories
No support plate needed.
Direct insertion into HTP500 marking system for printing.

Mounting instruction
23 mm
0.91"

1SNC160199S0201

113 mm4.45"

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

PB37

2

PAGE 35

Summary_3

3

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSSolution series
Blank markers and labels for MG3 thermal transfer printer

MG3 thermal transfer printer38

Support plates overview

40

MG3 kit and accessories

41

Terminal block identification42

Selection guide for terminal block markers
Terminal block markers

Other manufacturers' terminal block markers
End stop markers

MG-CPM-13

for SNK series

44

MG-CPM-…

for SNA and Solution series

44

MG-CPMF…

strip labels

45
46

MG-CPM-…
MG-TAA

62

RC810TT

48
70

MG-TAR
End stop label holders and covers

LH, LH-R1

for SNK series

49

PEB, PEBM, EPR1

for SNA and Solution series

50

PEAD, EPR2

for SNA and Solution series

51

MG-TDMslide-on cable markers

54

MG2-TDMO

clip-on cable markers

55

MG-ETFtie-on cable markers

57

MG-TPMABS cable markers (need label holder)

58

MG-TPMF

PVC cable markers (need label holder)60

3

Wire and cable identification
Selection guide for wire and cable markers
Wire and cable markers

Wire and cables label holders

52

56

UMH
PM, PM-ET, PM-AC

transparent label holder for MG-TPM

59

PMF, PMF-ET, PMF-ACtransparent label holder for MG-TPMF

61

MG-VYTfor dielectric requirements

63

MG-17.5A

for strip identification

64

MG-PTSfor push-button identification

65

Component and equipment identification
Self-adhesive labels

Pre-cut labels

Label holders and covers

62

MG-TAA

66

MG-TAP
MG-TAPW

9 mm width label

68

MG-TAP-CCS

transparent label

69

MG-TAR

17 mm width label

70

MG-PLC

for PLC's identification

71

RTR-TAP

15 mm pre-drilled rail

67

RTA-TAP

15 mm self-adhesive rail

67

RT-CCP

15 mm protective cover

67

RTA-TAPW

9 mm self-adhesive rail

68

Self-adhesive panel plates

MG-VRT-A

72

Rivet fixing panel plates

MG-VRT-R

72

Other manufacturers markers selection guide		

158

PAGE 37

Summary_3

Panel identification

MG3 thermal transfer printerThe versatile, compact androbust marking system
MARKINGenius® MG3 is a high resolution printer based onthermal transfer technology for producing high quality identification and labelling for terminal blocks, cables and all equipment mounted in electrical panels.
Compact, ergonomic, clean and quiet, MARKINGenius® MG3
may be conveniently located in an office or workshop or easilytransported in the field.
Thermal transfer technology uses heat to transfer charactersor symbols onto a plastic marker through an ink ribbon.
Besides the excellent printing quality, there is no drying time
and the markers are instantly usable.
With the MG3 thermal transfer printer, forget about drying
times and clogged print head problems.

3

Combined simplicity, performanceand make savings

Save time and consumables
Gain time with a short printing process:12 seconds cycle. Carriage loading and unloading
operation is fast and simple.
Economic: up to 300 000 markers with one ribbon.
Partially printed marker card may be reused to
avoid wastage.
No drying time: printed markers are immediately
ready to use.
Experience quality
High Quality printing: 300 x 600 dpi for image orgraphic printing.
Robust: all moving parts are in metal.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSHigh quality printing

Short printing cycle of 12 seconds

Economic: up to 300 000 markers
with one ribbon

Many media types available forprinting

1SNC160211S0201

Facilitate your printing process
Compact design (382 x 230 x 230 mm) facilitates
use in workshops or in the field.
Easy to install and use: comprehensive quickstart kit. Intuitive software with easy data importand entry.
Versatile: many different media available: plastic
markers, stickers, labels etc.

MG3 thermal transfer printerComponents of the kit

The MG3 printer is delivered with a comprehensive set ofaccessories for getting started quickly
Kit (Part number: 1SNB419001R0000) including:–– 1 Thermal transfer printer–– 1 Software CD–– 1 Power supply cable–– 1 USB cable–– 1 Installation, operating, maintenanceand user documentation–– 1 Protective cover–– 1 Ribbon take up spool–– 1 MG2-QTB support plate for terminal block markers(MG-CPM-01, 02, 03, 04, 07)–– 1 MG2-PWC support plate for wire and cable markers(MG-TPM)–– 1 MG2-PLT support plate for wire and cable markers(MG-TPMF) and various labels and signs–– 1 MG2-ETB Support plate for SNK series terminal block
markers (MG-CPM-13)–– 1 MG2-ETR Black printing ribbon.

– – Optimised printing of media for cables, terminal blocks,
control gear, connectors, push buttons, components,
panels and self-adhesive labels– – Specially developed proprietary Genius font and also
Windows fonts– – Designs customised media– – Vector, drawing and clip art printing– – Free upgrades for each new release– – Microsoft® Windows® XP, Windows Vista®,
Windows 2000 SP4 ®, Windows 7®.

1SNC160211S0201

Genius Pro software
The Genius Pro software application benefits from long experience in the field and requires the operator to have only basic
skills in order to use it. It is application-oriented and provides
fast and easy data entry including a dynamic full-size media
preview giving an accurate representation of the current job.
Features / characteristics:–– More than ten types of counter such as *.txt, *.cad, *.dbf,*.xls can be imported–– AutoCAD, Elcad, Spac and Excel import–– MATRIX, ACS and Simplo conversion

3

PAGE 39

MG3 thermal transfer printerFind out quickly which support plate your printing job needs
Support plates included in MG3 Kit

Support plate typeMarkers and labels compatibles
Terminal block markers

MG2-PWC

MG2-PLT

MG2-QTB

MG-CPM-01

MG2-ETB(except 5x7 mm)

Terminal block marker strips






















Support plates to be purchased separately

Support plate typeMarkers and labels compatibles
Terminal block markers

MG2-PTD

MG2-PTM

MG2-WTB

MG2-STB

MG2-CTB

MG-CPM-01

MG2-MTB

MG2-LTB

(5x7 mm only)

Slide-on cable markers
Clip-on cable markers

MG-CPM-05
MG-CPM-06
MG-CPM-09
MG-CPM-10
MG-CPM-12
MG-TDM
MG2-TDMO







4x12 mm4x16 mm

1SNC160212S0201

3

Tie-on cable labels
Slide-in cable markers
Slide-in cable markers
LabelsLabelsLabels 9 mm
CCS Transparent markers
Self-adhesive labels
Self adhesive labels
PLC labels
Modular self-adhesive labels
Push button labels
Panel plates

MG-CPM-02
MG-CPM-03
MG-CPM-04
MG-CPM-07
MG-CPM-13
MG-CPMF
MG-CPMFA
MG-ETF
MG-TPM
MG-TPMF
MG-TAR
MG-TAP
MG-TAPW
MG-TAP
MG-TAA
MG-VYT
MG-PLC
MG-17.5
MG-PTS
MG-VRT

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSMG3 thermal transfer printerKit and accessories
Description–– Versatile,–– Compact and robust,–– Easy to install and use.

Ordering details
Description
MG3 KITColor

MG3 Thermal transfer printer KIT
List of items included in the KIT:
1 MG3 Thermal transfer printer1 Software CD
1 Power supply cable
1 USB cable
1 Protective cover
1 Ribbon take up spool
1 Black monochrome ribbon
1 Support plate for cable tags MG-TPM
1 Support plate for labels, cables, plates andvarious markers
1 Support plate for terminal block markers
MG-CPM-01(5x10 and 5x15),02,03,04,07
1 Support plate for SNK series terminal block
markers (MG-CPM-13)

Type
MG3 KITPart Number
1SNB419001R0000

Pkg

Weightpce(1 pce) g

1

12600.00

MG3
MG3 SOFTWARE
MG3 POWER
MG3 USB
MG2 COVE 991680
MG2-CRB 991654
MG2-ETR 991600
MG2-PWC 991000
MG2-PLT 991002
MG2-QTB 991011
3

MG2-ETB 991016

Support plates
Description

Color

Type

Part Number

Pkg
pce

Support plate MG2-...

Support template for:
Cable tags MG-TPM
Labels, cable tags, plates and various markers
Terminal block markers MG-CPM-05,12
Terminal block markers MG-CPM-06
Terminal block markers MG-CPM-10
Cable tags MG-TDM (4x12 mm)
Terminal block markers MG-CPM-01 (5x7 mm)
Cable tags MG2-TDMO and MG-TDM (4x16 mm)
Terminal block markers MG-CPM-01(5x10 and 5x15 mm),02,03,04,07
Terminal block markers TE Connectivity RC andMC series
Terminal block markers MG-CPM-09
Terminal block markers SNK series MG-CPM-13

Weightg(1 pce)MG2-PWC 991000
MG2-PLT 991002
MG2-WTB 991004
MG2-STB 991005
MG2-CTB 991006
MG2-PTD 991007
MG2-MTB 991008
MG2-PTM 991010
MG2-QTB 991011

1SNB991000R0000
1SNB991002R0000
1SNB991004R0000
1SNB991005R0000
1SNB991006R0000
1SNB991007R0000
1SNB991008R0000
1SNB991010R0000
1SNB991011R0000

1
1
1
1
1
1
1
1
1

148.00148.00151.00158.00156.00126.00149.00116.00120.00MG2-ABM 991012

1SNB991012R0000

1

146.00

MG2-LTB 991013
MG2-ETB 991016

1SNB991013R0000
1SNB991016R0000

1
1

128.00100.00TypePart Number

PET blank cover for support plate
Description

Color

Pkg
pce

PET blank for support plate MG2-PWC
PET blank for support plate MG2-PLT
PET blank for support plate MG2-PTD
PET blank for support plate MG2-MTB
PET blank for support plate MG2-WTB
PET blank for support plate MG2-STB
PET blank for support plate MG2-CTB
PET blank for support plate MG2-QTB
PET blank for support plate MG2-ETB

MG2-TWC 991502
MG2-TLT 991522
MG2-TTD 991563
MG2-TMT 991513
MG2-TWT 991542
MG2-TST 991552
MG2-TCT 991562
MG2-TGT 991532
MG2-TTB 991512

1SNB991502R0000
1SNB991522R0000
1SNB991563R0000
1SNB991513R0000
1SNB991542R0000
1SNB991552R0000
1SNB991562R0000
1SNB991532R0000
1SNB991512R0000

3
3
3
3
3
3
3
3
3

Type

Part Number

Pkg

Weight
g
16.70
14.70
11.70
12.00
12.00
21.50
12.00
11.70
10.70

(1 pce)Accessories
Color

pce

Print head cleaning kit
Black monochrome ribbon
Blue monochrome ribbon
Red monochrome ribbon
Green monochrome ribbon
White monochrome ribbon

Black
Blue
Red
Green
White

MG2-CKP 991670
MG2-ETR 991600
MG2-ETR 991601
MG2-ETR 991602
MG2-ETR 991603
MG2-ETR 991606

1SNB991670R0000
1SNB991600R0000
1SNB991601R0000
1SNB991602R0000
1SNB991603R0000
1SNB991606R0000

1
1
1
1
1
1

Weightg
336.00227.00229.00
255.00247.00333.00(1 pce)Ribbons MG2-ETR...

PAGE 41

1SNC160112S0201 - Rev. A

Description

MG3 markers selection guide
Terminal block blank markers selection guide
Terminal blocks (Terminal blocks styles not listed on the chart do not have a marker compatible with this printer)
Connection technology

Terminal blockpart number

Marker typeMarker mounting

Screw clamp

1SNK...

Individual marker (3)Top and side marking

Adhesive strip label

Top and side marking

Individual marker (3)Side marking

Strip marker

Side marking

Strip label

Side marking

Individual marker (3)Top and side marking

Adhesive strip label

Top and side marking

Individual marker (3)Top marking

1SNA... (1)PI-Spring

Spring clamp

1SNK...

1SNA...

Side marking
3

Spring loaded
screw clamp

Pluggablescrew clamp

1SNA...

1SNA...

Strip marker

Side marking

Strip label

Side marking

Individual marker (3)Side marking

Strip marker

Side marking

Individual marker (3)Side marking(1) Except mini-blocks.
(3) Can be strip mounted when marker spacing = terminal block spacing.

Special terminal blocks (Terminal blocks styles not listed on the chart do not have a marker compatible with this printer)D4/6.T...

1SNA...

Strip label

Side marking

D2.5/6.D...

1SNA...

Strip label

Side marking

D4/6.P.T1

1SNA...

Strip label

Side marking

SNK series end stop and label holders
BAZ1

Individual
marker

BAM4
LH (label holder for BAM4, BAZH1, BAZ1)Label

Top marking

MG-CPM 13 41790

Top and sidemarking

MG-CPM 13 41791(6 mm spacing)

Top marking

MG-TAA 49498

LH-R1 (label holder for BAM4, BAZH1, BAZ1)
Wire marker

Top marking

MG2-TDMO
1SNC160213S0201 - Rev. A

UMH (Universal wire markers holder for BAM4, BAZ1)

MG-TAA 49198
MG-TAR 45194

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSTerminal blocks spacing
5 mm
5.08 mm
5.2 mm
6 mm
8 mm
0.197 in
0.200 in
0.205 in
0.236 in
0.315 in
MG-CPM-13 MG-CPM-13
41790
41791

10 mm
0.394 in

12 mm
16 mm
0.472 in
0.630 in
MG-CPM-13 41791 (2)22 mm
0.866 in

26 mm
1.024 in

31 mm
1.220 in

36 mm
1.417 in

MG-CPMFA 43196
MG-CPM-03
41291

MG-CPM-04 41390 (2)MG-CPM-04 MG-CPM-04
41391
41396

MG-CPMF
43090

MG-CPMF 43090
MG-CPM-13 MG-CPM-13
41790
41791

MG-CPM-13 41791 (2)MG-CPMFA 43196

MG-CPM-05
41490

MG-CPM-05 41490 (2)MG-CPM-01
41094
MG-CPM-12
46391
MG-CPMF
43094

MG-CPM-01 41094 (2)3MG-CPMF 43094
MG-CPM-04 41390 (2)MG-CPM-04
41391
MG-CPM-03
41291(2) Marker width < marking's area size - markers must be mounted individually.

MG-CPMF
43094
MG-CPMF
43094
MG-CPMF
43094

SNA series end stop and label holders
BAM2, BADL, BADH

Individual
markerTop and sidemarking

RC810TT

BADRL

Individual
marker

Top marking

MG-CPM 04 41391

BAMH
PEAD (Label holder for BAM2 and BADL)Label

Top marking

RC810TT

MG3 terminal block markers areavailable in various versions adapted
to the usual identification
requirements of your terminal blocks.

MG-TAA 49198
MG-TAR 45194

Individual
markersStripmarkers

Striplabels

PAGE 43

1SNC160213S0201 - Rev. A

PEB (Label holder for
BAM2, BADL, BADH, BAMH, BAR and BADRL)MG-TAPW 49096

MG-CPM terminal block markers
Blank markers for SNK, SNA and Solution series
Description

1SNC160131F0014–– Available in different versions to suit all terminal block formats,–– Partially printed marker cards may be re-used to avoid wastage,–– Made of halogen free self-extinguishing polycarbonate,–– Refer to MG3 markers' selection guide for terminal blocks and end stop markers to find the suitable
marker for your needs.

MG-CPM-13

Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-40°C to +140°C -40°F to +284°F

Ordering details
Spacing

Dimensions

mm

mm

in

in

Nb. ofColormarkers
per card

Type

Part Number

SW
code

Pkg

Weightmarker (1 marker) g

SNK series terminal block markers
MG-CPM-13
Individual markers for SNK series terminal blocks, can be strip mounted when marker and terminal block spacing are equal.
5.2
0.205
5 x 12 0.197 x 0.472 56
White
MG-CPM-13 41790 1SNB041790R0512 113
1960
0.20
Yellow
MG-CPM-13 41740 1SNB041740R0512 113
1960
0.20
6
0.236
6 x 12 0.236 x 0.472 48
White
MG-CPM-13 41791 1SNB041791R0612 114
1680
0.30
Yellow
MG-CPM-13 41741 1SNB041741R0612 114
1680
0.30
Support plate
Included in the MG3 Kit
MG2-ETB 991016 1SNB991016R0000
1
100.00

SNA and Solution series terminal block markers
MG-CPM-01
Individual markers, can be strip mounted when marker and terminal block spacing are equal.
5.1
0.201
5x7
0.197 x 0.276 56
White
MG-CPM-01 41094 1SNB041094R0507 13
Support plate
Purchased separately
MG2-MTB 991008 1SNB991008R0000

1960
1

0.20
149.00MG-CPM-03
Individual markers, can be strip mounted when marker and terminal block spacing are equal.
50.197
5 x 10 0.197 x 0.394 56
White
MG-CPM-03 41291 1SNB041291R0510 25
Support plate
Included in the MG3 Kit
MG2-QTB 991011 1SNB991011R0000

1960
1

0.20
120.00MG-CPM-04
Individual markers, can be strip mounted when marker and terminal block spacing are equal.
80.315
5 x 10 0.197 x 0.394 32
White
MG-CPM-04 41390 1SNB041390R0510
Yellow
MG-CPM-04 41340 1SNB041340R0510
Strip markers
6
0.236
6 x 10 0.236 x 0.394 48
White
MG-CPM-04 41391 1SNB041391R0610
80.315
8 x 10 0.315 x 0.394 36
MG-CPM-04 41396 1SNB041396R0810
Support plate
Included in the MG3 Kit
MG2-QTB 991011 1SNB991011R0000

42
42

1680
1680

0.30
0.40

45
48

1344
1120

0.20

1

120.00MG-CPM-05
Individual markers
50.197
5 x 10Support plate
Purchased separately

0.197 x 0.394 56

White

MG-CPM-05 41490 1SNB041490R0510 51

1960

MG2-WTB 991004

1

1SNB991004R0000

0.40
151.00MG-CPM-12
Flexible pitch strip markers
5 ... 6 0.197 ... 0.236 4.2 x 9 0.165 x 0.354 56
Support plate
Purchased separately

White

MG-CPM-12 46390 1SNB046390R4209 112

1960

MG2-WTB 991004

1

1SNB991004R0000

0.20
151.00

Refer to selection page for information on strip markers.
1SNC160165S0201

3

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

MG-CPMF terminal block markers
Blank strip labels for SNK, SNA and Solution series
Description–– To be directly used on terminal block assembly,–– Available in precut or self-adhesive versions to fit all applications.

MG-CPMF

Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

SW
code

Pkg

Weightmarker (1 marker) g

SNA and Solution series terminal block markers
MG-CPMF
Strip labels for all terminal blocks from the SNA and Solution series
5.2 x 105 0.205 x 4.134 20
White
MG-CPMF 43094
7.6 x 105 0.299 x 4.134 12
White
MG-CPMF 43091
10 x 105
0.394 x 4.134 10
White
MG-CPMF 43090

1SNB043094R0052 551
1SNB043091R0076 552
1SNB043090R0010 530

1000
600
500

0.30
1.00
1.20
3

SNK series terminal block markers
MG-CPMFA
Self-adhesive strip labels for all terminal blocks from the SNK series
12 x 105
0.472 x 4.134 8
White
MG-CPMFA 43196
Yellow
MG-CPMFA 43146

1SNB043196R0012 330
1SNB043146R0012 330

400
400

2.60
2.60

MG-CPMFA 46990

1SNB046990R0010 530

100

6.23

MG2-PLT 991002

1SNB991002R0000

1

148.50Component and equipment markers
MG-CPMFA
Self-adhesive strip labels for various applications
10 x 105
0.394 x 4.134 10
White

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

Mounting instruction

1SNC160166S0201 - Rev. A

1SNC160132F0014

Main technical data

PAGE 45

MG-CPM terminal block markers
Blank markers for other manufacturers
Description

1SNC160120F0014–– Available in different versions to suit other manufacturers terminal block formats,–– Partially printed marker cards may be re-used to avoid wastage,–– Made of halogen free self-extinguishing polycarbonate,–– Refer to MG3 markers' selection guide for other manufacturer terminal blocks and end stop markers tofind the suitable marker for your needs.

Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-40°C to +140°C -40°F to +284°F

MG-CPM-01

Ordering details
Spacing

Dimensions

mm

mm

in

in

Nb. ofColormarkers
per card

Type

Part Number

SW
code

Pkg

Weightmarker (1 marker) g

MG-CPM-01
0.197 x 0.394 56
0.197 x 0.591

0.197 x 0.276 56

White
White

White

MG-CPM-01 41090N 1SNB041090R0510 14
MG-CPM-01 41091N 1SNB041091R0515 16

1960
1680

MG2-QTB 991011

1SNB991011R0000

1

MG-CPM-01 41094

1SNB041094R0507 13

1960

MG2-MTB 991008

1SNB991008R0000

1

0.20
0.20
120.000.20
149.00MG-CPM-02
Individual markers
5.1
0.201
5 x 100.197 x 0.394 56

White
Yellow

Support plate
Included in the MG3 Kit

MG-CPM-02 41190N 1SNB041190R0510 22
MG-CPM-02 41140N 1SNB041140R0510 22

1680
1680

MG2-QTB 991011

1SNB991011R0000

1

MG-CPM-03 41291
MG-CPM-03 41293

1SNB041291R0510 25
1SNB041293R0510 25

1960
1960

MG2-QTB 991011

1SNB991011R0000

1

0.40
0.40
120.00MG-CPM-03
Individual markers
50.197
5 x 100.197 x 0.394 56

White
White

Support plate
Included in the MG3 Kit

0.20
0.20
120.00MG-CPM-04
Individual markers
80.315
5 x 10
Strip markers
6
0.236
6 x 105.2
0.205
5 x 10Support plate
Included in the MG3 Kit

0.197 x 0.394 32

White
Yellow

MG-CPM-04 41390
MG-CPM-04 41340

1SNB041390R0510 41
1SNB041340R0510 41

1680
1680

0.30
0.40

0.236 x 0.394 48
0.197 x 0.394

White
White

MG-CPM-04 41391
MG-CPM-04 41395

1SNB041391R0610 45
1SNB041395R0510 31

1344
1680

0.20
0.30

MG2-QTB 991011

1SNB991011R0000

1

120.00MG-CPM-05
Individual markers
50.197
5 x 10
Strip markers
50.197
5 x 10Support plate
Purchased separately

0.197 x 0.394 56

White

MG-CPM-05 41490

1SNB041490R0510 51

1960

0.40

0.197 x 0.394 56

White

MG-CPM-05 41494

1SNB041494R0510 51

1960

0.20

MG2-WTB 991004

1SNB991004R0000

1

MG-CPM-06 41591

1SNB041591R0510 61

1540

MG2-STB 991005

1SNB991005R0000

151.00MG-CPM-06
Individual markers
6
0.236
5 x 10Support plate
Purchased separately

0.197 x 0.394 44White

See other manufacturers selection guide at the end of this catalogue

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1

0.20
158.00Continue on next page →1SNC160167S0201

3

Individual markers
5.1
0.201
5 x 105 x 15
Support plate
Included in the MG3 Kit
Individual markers
5.1
0.201
5x7
Support plate
Purchased separately

MG-CPM terminal block markers
Blank markers for other manufacturers
Ordering details
Spacing

Dimensions

mm

mm

in

Nb. ofColormarkers
per cardin

TypePart Number

SW
code

Pkg

Weightmarker (1 marker) g← Continuation of previous page
MG-CPM-07
Individual markers
5.2
0.205
5 x 10Support plate
Included in the MG3 Kit

0.197 x 0.394 48

White

MG-CPM-07 41691

1SNB041691R0510 711680

MG2-QTB 991011

1SNB991011R0000

1

MG-CPM-09 41890

1SNB041890R0510 92

1960

MG2-LTB 991013

1SNB991013R0000

1

MG-CPM-10 46192

1SNB046192R0512 101

1680

MG2-CTB 991006

1SNB991006R0000

1

MG-CPM-12 46390
MG-CPM-12 46391

1SNB046390R4209 112
1SNB046391R4206 111

1960
1960

MG2-WTB 991004

1SNB991004R0000

1

0.30
120.00MG-CPM-09
Flexible pitch strip markers
5 ... 6 0.197 ... 0.236 5 x 10 0.197 x 0.394 56
Support plate
Purchased separately

White

0.20
128.00MG-CPM-10
Individual markers
5.5
0.217
5 x 12
Support plate
Purchased separately

0.197 x 0.472 48

White

0.30
156.003MG-CPM-12
Flexible pitch strip markers
5 ... 6 0.197 ...
4.2 x 9 0.165 x 0.354 56
0.236
4.2 x 6 0.165 x 0.236
Support plate
Purchased separately

White
White

0.20
0.20
151.00See other manufacturers selection guide at the end of this catalogue

Mounting instruction(1)(1) Individual marker(2) Strip marker(3) Flexible pitch strip marker(3.1) Flexible pitch strip marker with pitch aligned to terminal
block spacing

(3)

a

b

a

b

a = marker widthb = marker spacingc = extended marker spacing

(3.1)

(2)

c
b

1SNC160167S0201

a

PAGE 47

RC810TT end stop markers
Blank markers for BAM2, BADL, BADH

1SNC160246F0014

Description

RC810TT–– Blank marker card designed for high marking quality,–– Excellent marking durability in the most severe environments,–– Made of rigid polycarbonate.

Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-50°C to +120°C -58°F to +248°F

Ordering details
Dimensions
mminMaximumNb. ofColor
printed digits markers
Hor. Vert. per card

TypePart Number

SW
code

Pkg

Weightcard(1 card) g

SNA and Solution series markers
RC810TT
10 x 8 0.394 x 0.315 4

7

30

White
Yellow

RC810TT
RC810TT-YL

1SNA234600R1000 138
1SNA234700R1400 138

22
22

12.00
12.00

MG2-ABM 991012

1SNB991012R0000

1

146.003Marking system accessories
MG2-ABM
Support plate
Support template for terminal block markers RCTT and MC series

BAM2
1SNA206351R1600

BADL
1SNA399903R0200

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSBADH
1SNA116900R2700

BAMH
1SNA114836R0000

1SNC160187S0201 - Rev. B

Compatible end stopsLH, LH-R1 end stop label holders
For MG-TAA and MG-TAR labels
Description

1SNK160210F0014–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Main technical data
Material
Polyamide

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Spacingmm

Dimensions
in

mm

Color

Type

Part Number

SW
code

in

Pkg

Weightpce(1 pce) g

50

0.60

50

1.10

For MG-TAA 49498 and MG-TAA 49448
LH
100.35 x 1.18

Dark GreyLH

1SNK900605R0000

For MG-TAA 49198, MG-TAA 49148 and MG-TAR 45194
LH-R1
19.5 0.768

LH-R1

8.8 x 303

17.9 x 35.65

0.70 x 1.40

Dark Grey

LH-R1

1SNK900607R0000

Dimensions given apply to the labelling area.

Compatible end stops

BAM4
1SNK900001R0000

BAZ1
1SNK900002R0000

1SNC160180S0201

LH

0.394

BAZH1
1SNK900102R0000

PAGE 49

PEB end stop label holders
For MG-TAA and MG-TAR labels
Description–– To be used for terminal block assembly identification,–– Direct insertion onto end stops from SNA series.

1SNC160200F0014

Main technical data

PEB

Material
Polyamide (PEB)
PVC (EPR1)

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensions
mm

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

50

1.70

1SNA178431R2200

1

0.054

1SNA113084R0100

50

2.80

in

PEB
Label holder for end stop 35 x 17 mm 1.378 x .669 in, to be snapped onto end stop
18 x 35.5
0.709 x 1.378
GreyPEB
1SNA113077R1100
EPR1
Card of 54 PVC protective covers
17.5 x 35
0.689 x 1.378

Transparent

EPR1

PEBM
"All in one": PEB marker holder with marker and protection included
PEBM

Compatible end stops

BAM2
1SNA206351R1600

BADL
1SNA399903R0200

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSBADH
1SNA116900R2700

BAMH
1SNA114836R0000

BAR
1SNA164519R2400

BADRL
1SNA199420R2100

1SNC160188S0201 - Rev. A

3

PEAD end stop label holders
For MG-TAPW49096 label
Description

PEAD

Main technical data
Material
Polyamide

Flammability
V0

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

20

0.78

1

4.00

PEAD
Label holder for end stop, compatible with MG-TAPW49096 markers and EPR2 cover.
9 x 290.354 x 1.142
Grey
PEAD
1SNA399719R1000
EPR2
Card of 20 covers compatible with MG-TAPW 49096 and 49046.
9 x 290.354 x 1.142
Transparent
EPR2

1SNA399726R0700

3

Dimensions given apply to the labelling area.

Compatible end stops

BAM2
1SNA206351R1600

1SNC160189S0201 - Rev. A

1SNC160058F0014–– Easily identify your terminal block assemblies with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with MG-TAPW 49096 and 49046,–– Compatible with BAM2 and BADL SNA series end stops.

BADL
1SNA399903R0200

PAGE 51

MG3 wire and cable markers
Selection guide
Fast and direct
wire and cable identification
Save time on your cable identification job
by using direct insertion cable markers
MG-TDM, MG-TDMO or MG-ETF.
Directly print the marker and attached it
to the cable of your choice.

MG-TDM
Slide-on cable marker

MG-TDMO
Clip-on cable marker

MG-ETF
Tie-on cable marker

MG-TPMF

MG-TPM

Easy entry thanks to profiled shape

For more efficiency, stems can becable tied together using the holes
provided

Evolutive and protected wire andcable identification

For fast and easy cable identification
Markers directly mounted on wires and cables

Wire external diametermm
Ø 1.6 ... 3.25

Ø 2 ... 2.9

Ø 2.9 ... 3.5

Ø 2 ... 4.4

Ø 4 ... 4.6

inØ 0.06 ... 0.12

Ø 0.07 ... 0.11

Ø 0.11 ... 0.14

Ø 0.07 ... 0.17

Ø 0.16 ... 0.18

Conductor
sectionmm²
0.5 ... 1.5

0.5 ... 1.5

1.5 ... 2.5

1 ... 6

4 ... 6

Marker length
mm
12

in
0.472

16

0.630

12

0.472

16

0.630

12

0.472

16

0.630

12

0.472

16

0.630

12

0.472

16

0.630

Marker color

Slide-on cable marker
MG-TDM

Clip-on cable marker
MG2-TDMOWhiteYellowWhite
YellowWhite
YellowWhite
YellowWhite
YellowWhite
YellowWhite
YellowWhite
YellowWhite
YellowWhite
Yellow

MG-TDM-01 49190
MG-TDM-01 40140
MG-TDM-01 49191
MG-TDM-01 40141
–
–
–
–
–
–
–
–
MG-TDM-02 40290
MG-TDM-02 40240
MG-TDM-02 40291
MG-TDM-02 40241
–
–
–
–

–
–
–
–
MG2-TDMO-01 40390
MG2-TDMO-01 40340
MG2-TDMO-01 40391
MG2-TDMO-01 40341
MG2-TDMO-02 40490
MG2-TDMO-02 40440
MG2-TDMO-02 40491
MG2-TDMO-02 40441––––
MG2-TDMO-03 40590
MG2-TDMO-03 40540
MG2-TDMO-03 40591
MG2-TDMO-03 40541

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160214S0201

3

Each individual label and label holder
is easily detached from the stem for
installation onto cable. The printed label
in its holder is perfectly protected overtime.

For evolutive identification
Marker holders + slide-in markers

V1

L1

3
14B
Wire external diametermm
Ø 1.3 ... 2.2

inØ 0.051 ... 0.087

Conductor
sectionmm²0.25 ... 0.5

Ø 2 ... 3.7

Ø 0.079 ... 0.146

0.5 ... 2.5

Ø 3.5 ... 4.3

Ø 0.138 ... 0.169

2.5 ... 4Ø 4 ... 6.3

Ø 0.157 ... 0.248

4 ... 10

Ø 6 ... 10Ø 0.236 ... 0.394

10 ... 25

Ø 9 ... 15

Ø 0.354 ... 0.591

25 ... 70

Ø 14 ... 26

Ø 0.551 ... 1.024

70 ... 240

Label holder length

Slide-on cable marker
holder for PVC labels
PM

mm
10
12
15
10
12
15
10
12
15
10
12
15
10
12
15
10
12
15
10
12
15

–
–
–
PM-01 50100
PM-01 50110
PM-01 50120
PM-02 50200
PM-02 50210
PM-02 50220
PM-03 50300
PM-03 50310
PM-03 50320
PM-04 50400
PM-04 50410
PM-04 50420
PM-05 50500
PM-05 50510
PM-05 50521
PM-06 50600
PM-06 50610
PM-06 50620

in
0.394
0.472
0.591
0.394
0.472
0.591
0.394
0.472
0.591
0.394
0.472
0.591
0.394
0.472
0.591
0.394
0.472
0.591
0.394
0.472
0.591

2
13Q

Compatible labels

Slide-on cable marker
holder for ABS labels
PMF

Compatible labels–––
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092

PMF-00 90000
PMF-00 90020
PMF-00 90010
PMF-01 90100
PMF-01 90110
PMF-01 90120
PMF-02 90200
PMF-02 90210
PMF-02 90220
PMF-03 90300
PMF-03 90310
PMF-03 90320
PMF-04 90400
PMF-04 90410
PMF-04 90420
PMF-05 90500
PMF-05 90510
PMF-05 90520–––

MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
–
–
–

3

Label holders are given for biggest packaging. For smaller packaging see product page. Compatible labels are given in White color, see product page for more colors.

For identification of thick tubes
Tie-on markers / label holdersmm
13 x 57in
0.512 x 2.244

12
15

0.472
0.591

Marker color Marker holder
color
White
Yellow
White
White

–
–
Transparent
Transparent

MG-ETF

PM-ET

Compatible marker

PMF-ET

Compatible marker

MG-ETF 54192
MG-ETF 54142––––
PM-ET 53010
PM-ET 53020––
MG-TPM 40091
MG-TPM 40092–––
PMF-ET 63020–––
MG-TPMF 42092B

1SNC160214S0201

Marker / Marker holder length

PAGE 53

MG-TDM wire and cable markers
Slide-on cable blank markers
Description

1SNC160117F0014–– To be directly printed and slided onto the wire,–– Partially printed marker cards may be re-used to avoid wastage,–– Made of rigid polycarbonate.

MG-TDM-01

Main technical data
Material
Polycarbonate

Flammability
V0

Temperature range-40°C to +140°C -40°F to +284°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

SW
code

Pkg

Weightmarker (1 marker) g

Cable Ø 1.6-3.25 mm 0.06-0.12 in Section 0.5-1.5 mm²
MG-TDM-01 Length 12 mm 0.472 in
4 x 120.157 x 0.472 66
Support plate
Purchased separately
MG-TDM-01 Length 16 mm 0.630 in
4 x 160.157 x 0.630 40

White
Yellow

Support plate
Purchased separately

MG-TDM-01 40190
MG-TDM-01 40140

1SNB040190R0412 121
1SNB040140R0412 121

1320
1320

0.30
0.30

MG2-PTD 991007

1SNB991007R0000

1

126.00MG-TDM-01 40191
MG-TDM-01 40141

1SNB040191R0416 123
1SNB040141R0416 123

800
800

0.30
0.30

MG2-PTM 991010

1SNB991010R0000

1

116.00MG-TDM-02 40290
MG-TDM-02 40240

1SNB040290R0412 122
1SNB040240R0412 122

1056
1056

MG2-PTD 991007

1SNB991007R0000

1

126.00MG-TDM-02 40291
MG-TDM-02 40241

1SNB040291R0416 124
1SNB040241R0416 124

640
640

0.40
0.40

MG2-PTM 991010

1SNB991010R0000

1

116.00

Cable Ø 2-4.4 mm 0.07-0.17 in Section 1-6 mm²
MG-TDM-02 Length 12 mm 0.472 in
4 x 120.157 x 0.472 66

White
Yellow

Support plate
Purchased separately
MG-TDM-02 Length 16 mm 0.630 in
4 x 160.157 x 0.630 40
Support plate
Purchased separately

White
Yellow

0.30
0.30

Mounting instruction

1SNC160168S0201

3

White
Yellow

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

MG2-TDMO wire and cable markers
Clip-on cable blank markers
Description–– To be directly printed and clip onto the wire,–– Partially printed marker cards may be re-used to avoid wastage,–– Made of rigid polycarbonate.

MG2-TDMO-01

Material
Polycarbonate

Flammability
V0

Temperature range-40°C to +140°C -40°F to +284°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

SW
code

Pkg

Weightmarker (1 marker) g

Cable Ø 2-2.9 mm 0.07-0.11 in Section 0.5-1.5 mm²
MG2-TDMO-01
4 x 120.157 x 0.472 40
4 x 160.157 x 0.630

White
YellowWhite
Yellow

MG2-TDMO-01 40390
MG2-TDMO-01 40340
MG2-TDMO-01 40391
MG2-TDMO-01 40341

1SNB040390R0412
1SNB040340R0412
1SNB040391R0416
1SNB040341R0416

125
125
128
128

880
800
880
800

0.30
0.30
0.30
0.30

1SNB040490R0412
1SNB040440R0412
1SNB040491R0416
1SNB040441R0416

126
126
129
129

640
640
640
640

0.40
0.40
0.40
0.40

MG2-TDMO-03 40590
MG2-TDMO-03 40540
MG2-TDMO-03 40591
MG2-TDMO-03 40541

1SNB040590R0412
1SNB040540R0412
1SNB040591R0416
1SNB040541R0416

127
127
130
130

560
560
560
560

0.40
0.40
0.40
0.40

MG2-PTM 991010

1SNB991010R0000

1

116.003

Cable Ø 2.9-3.5 mm 0.11-0.14 in Section 1.5-2.5 mm²
MG2-TDMO-02
4 x 120.157 x 0.472 40
4 x 160.157 x 0.630

White
YellowWhite
Yellow

MG2-TDMO-02 40490
MG2-TDMO-02 40440
MG2-TDMO-02 40491
MG2-TDMO-02 40441

Cable Ø 4-4.6 mm 0.16-0.18 in Section 4-6 mm²
MG2-TDMO-03
4 x 120.157 x 0.472 40
4 x 160.157 x 0.630

White
YellowWhite
Yellow

Marking system accessories
MG2-PTM
Support plate
Purchased separately

Mounting instruction

1SNC160169S0201 - Rev. A

1SNC160118F0014

Main technical data

Compatible holders

UMH

PAGE 55

1SNK160090F0014

UMH wire and cable marker holders
Universal wire marker holders

UMH

Description–– Compatible with most of the wire markers available on the market (wire markers not supplied with UMH),–– Quickly fit to any SNK terminal blocks and accessories: strip mounting of 10 parts for 5.2 mm 0.205 in
spacing, unitary mounting for other spacings

Main technical data
Material
Polyamide

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensionsmm
14.5 x 6

Nb. ofColormarkers
per card
in
0.571 x 0.236 10

Grey

Type

Part Number

UMH

1SNK900611R0000

Pkg

Weightpce(1 pce) g

10

0.20

3

Mounting instruction

1SNC160186S0201

Install the UMH on the terminal blocks (strip mounting) and slide on the wire
markers.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

MG-ETF wire and cable markers
Tie-on cable precut blank labels
Description

MG-ETF

Main technical data
Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm
13 x 57

Nb. ofColormarkers
per cardin
0.512 x 2.244 14

TypePart Number

SW
code

MG-ETF 54192
MG-ETF 54142

1SNB054192R1357 581
1SNB054142R1357 581

Pkg

Weightmarker (1 marker) g

White
Yellow

700
700

0.70
0.70

Marking system accessories

3

MG2-PLT
Support plate
Included in the MG3 Kit

MG2-PLT 991002

1SNB991002R0000

1

148.50

Mounting instruction

1SNC160170S0201

1SNC160119F0014–– Recommended for marking large diameter cables, hoses, tubes and conduits,–– To be used with cable ties (max. width 4.8 mm 0.19 in),–– Print area 15 x 20 mm 0.59 x 0.79 in,–– Made of rigid PVC.

PAGE 57

MG-TPM wire and cable markers
Slide-in precut blank labels
Description

1SNC160116F0014–– To be slided into PM holder,–– For cable up to 240 mm²,–– PM holders can be directly inserted on the markers without removing them from the stems,–– Made of rigid ABS.

Main technical data
Material
Acrylonitrile Butadienne Styrene (ABS)

MG-TPM

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensions
mm

3V1

14B

in

Nb. ofColormarkers
per card

MG-TPM
4 x 100.157 x 0.394 45
4 x 120.157 x 0.472
4 x 150.157 x 0.591

TypePart Number

SW
code

Pkg

Weightmarker (1 marker) g

White
White
White

MG-TPM 40090
MG-TPM 40091
MG-TPM 40092

1SNB040090R0410 1
1SNB040091R0412 2
1SNB040092R0415 3

2250
2250
2250

MG2-PWC 991000

1SNB991000R0000

1

0.30
0.30

3

Marking system accessories
MG2-PWC
Support plate
Included in the MG3 Kit

148.50PM

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

PM-ET

PM-AC

1SNC160171S0201

Compatible holders

PM, PM-ET and PM-AC transparent marker holders
For MG-TPM markers
Description
1SNC160251F0014–– Compatible with MG-TPM markers,–– Made of plasticised PVC.

Main technical data
Material
PVC

PM

Flammability
V0

Temperature range-40°C to +90°C -40°F to +194°F

Ordering details
Wire ext. diameter
mm

in

Wire
sectionmm²

Holderlength
mm in

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

For cable mounting
PM

PM-01

Profiled transparent holder to allow each type to accommodate a range of cable sizes
2 ... 3.7 0.079 ... 0.146 0.5 ... 2.5 10 0.394 Transparent
PM-01 50100
1SNB050100R0000
Transparent
PM-01 50102
1SNB050102R0001
Transparent
PM-01 50102-HF
1SNB050102R0002
12 0.472 Transparent
PM-01 50110
1SNB050110R0000
15 0.591 Transparent
PM-01 50120
1SNB050120R0000
Transparent
PM-01 50122
1SNB050122R0000
3.5 ... 4.3 0.138 ... 0.169 2.5 ... 4 10 0.394 Transparent
PM-02 50200
1SNB050200R0000
Transparent
PM-02 50202
1SNB050202R0000
12 0.472 Transparent
PM-02 50210
1SNB050210R0000
Transparent
PM-02 50212
1SNB050212R0000
15 0.591 Transparent
PM-02 50220
1SNB050220R0000
Transparent
PM-02 50222
1SNB050222R0000
4 ... 6.3 0.157 ... 0.248 4 ... 1010 0.394 Transparent
PM-03 50300
1SNB050300R0000
Transparent
PM-03 50302
1SNB050302R0000
12 0.472 Transparent
PM-03 50310
1SNB050310R0000
Transparent
PM-03 50312
1SNB050312R0000
15 0.591 Transparent
PM-03 50320
1SNB050320R0000
Transparent
PM-03 50322
1SNB050322R0000
6 ... 100.236 ... 0.394 10 ... 25 10 0.394 Transparent
PM-04 50400
1SNB050400R0000
Transparent
PM-04 50402
1SNB050402R0000
12 0.472 Transparent
PM-04 50410
1SNB050410R0000
Transparent
PM-04 50411
1SNB050411R0000
15 0.591 Transparent
PM-04 50420
1SNB050420R0000
Transparent
PM-04 50421
1SNB050421R0000
9 ... 150.354 ... 0.591 25 ... 70 10 0.394 Transparent
PM-05 50500
1SNB050500R0000
12 0.472 Transparent
PM-05 50510
1SNB050510R0000
15 0.591 Transparent
PM-05 50521
1SNB050521R0000
14 ... 26 0.551 ... 1.024 70 ... 240 10 0.394 Transparent
PM-06 50600
1SNB050600R0000
12 0.472 Transparent
PM-06 50610
1SNB050610R0000
15 0.591 Transparent
PM-06 50620
1SNB050620R0000

6000
2000
2000
5000
4000
1000
4000
1000
4000
1000
3000
1000
3000
1000
2000
500
2000
500
2000
500
1000
500
1000
500
500
500
250
500
250
250

0.20
0.20
0.10
0.20
0.20
0.20
0.30
0.30
0.30
0.30
0.35
0.35
0.30
0.30
0.40
0.40
0.45
0.45
0.45
0.45
0.50
0.50
0.60
0.60
0.70
0.80
1.10
1.30
1.40
2.70

Tie-on transparent holder for longitudinal mounting on cables, hoses, tubes and conduit (tie width max 6 mm 0.236 in)
12 0.472 Transparent
PM-ET 53010
1SNB053010R0000
2000
15 0.591 Transparent
PM-ET 53020
1SNB053020R0000
2000

0.40
0.50

3

PM-ET

PM-ET

For surface mounting
PM-AC
1SNB051000R0000
1SNB051010R0000
1SNB051020R0000

5000
4000
4000

0.20
0.20
0.30

Use holders only with designated cable marker of the same or a shorter length.
1SNC160172S0201 - Rev. A

PM-AC

Self-adhesive transparent holder to be used over all plane surfaces
10 0.394 Transparent
PM-AC 51000N
12 0.472 Transparent
PM-AC 51010N
15 0.591 Transparent
PM-AC 51020N

PAGE 59

MG-TPMF wire and cable markers
Slide-in precut blank labels
Description–– To be slided into PMF holder,–– For wire and cable up to 70 mm²,–– Made of rigid PVC.

Main technical data
1SNC160115F0014

Material
Rigid PVC

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details

MG-TPMF

Dimensions
mm

1
Q2L

13

in

Nb. ofColormarkers
per card

MG-TPMF4 x 100.157 x 0.394 112
4 x 120.157 x 0.472 80
4 x 150.157 x 0.591

TypePart Number

SW
code

Pkg

Weightmarker (1 marker) g

White
White
White

MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B

1SNB042090R0410 502
1SNB042091R0412 505
1SNB042092R0415 503

5600
4000
4000

MG2-PLT 991002

1SNB991002R0000

1

0.10
0.10
0.10

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

148.50Compatible holders

PMF

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSPMF-ET

PMF-AC

1SNC160173S0201

3

Flammability
V0PMF, PMF-ET and PMF-AC transparent marker holders
For MG-TPMF markers

PMF-00–– Compatible with MG-TPMF markers,–– Made of plasticised PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +90°C -40°F to +194°F

Ordering details
Wire ext. diameter
mm

in

Wire
sectionmm²

Holderlength
mm in

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

For cable mounting
PMF
Profiled transparent holder to allow each type to accommodate a range of cable sizes
1.3 ... 2.2 0.051 ... 0.087 0.25 ... 0.5 10 0.394 Transparent
PMF-00 90000
1SNB090000R0000
12 0.472 Transparent
PMF-00 90010
1SNB090010R0000
15 0.591 Transparent
PMF-00 90020
1SNB090020R0000
2 ... 3.7 0.079 ... 0.146 0.5 ... 2.5 10 0.394 Transparent
PMF-01 90100
1SNB090100R0000
12 0.472 Transparent
PMF-01 90110
1SNB090110R0000
15 0.591 Transparent
PMF-01 90120
1SNB090120R0000
3.4 ... 4.3 0.134 ... 0.169 2.5 ... 4
10 0.394 Transparent
PMF-02 90200
1SNB090200R0000
12 0.472 Transparent
PMF-02 90210
1SNB090210R0000
15 0.591 Transparent
PMF-02 90220
1SNB090220R0000
4 ... 6.3 0.157 ... 0.248 4 ... 1010 0.394 Transparent
PMF-03 90300
1SNB090300R0000
12 0.472 Transparent
PMF-03 90310
1SNB090310R0000
15 0.591 Transparent
PMF-03 90320
1SNB090320R0000
6 ... 100.236 ... 0.394 10 ... 25
10 0.394 Transparent
PMF-04 90400
1SNB090400R0000
12 0.472 Transparent
PMF-04 90410
1SNB090410R0000
15 0.591 Transparent
PMF-04 90420
1SNB090420R0000
9 ... 150.354 ... 0.591 25 ... 70
10 0.394 Transparent
PMF-05 90500
1SNB090500R0000
12 0.472 Transparent
PMF-05 90510
1SNB090510R0000
15 0.591 Transparent
PMF-05 90520
1SNB090520R0000

8000
7000
6000
6000
5000
4000
4000
4000
3000
3000
2000
2000
2000
1000
1000
500
500
250

0.10
0.10
0.10
0.20
0.20
0.20
0.20
0.30
0.30
0.40
0.40
0.50
0.40
0.60
0.70
0.90
1.10
1.40

Tie-on transparent holder for longitudinal mounting on cables, hoses, tubes and conduit (tie width max 6 mm 0.236 in)
15 0.591 Transparent
PMF-ET 63020
1SNB063020R0000
2000

0.40

3

PMF-ETFor surface mounting
PMF-AC
Self-adhesive transparent holder to be used over all plane surfaces
10 0.394 Transparent
PMF-AC 66000N
12 0.472 Transparent
PMF-AC 66010N
15 0.591 Transparent
PMF-AC 66020N
20 0.787 Transparent
PMF-AC 66040N

1SNB066000R0000
1SNB066010R0000
1SNB066020R0000
1SNB066040R0000

5000
4000
4000
4000

0.20
0.20
0.30
0.30

Use holders only with designated cable marker of the same or a shorter length.

1SNC160174S0201

1SNC160251F0014

Description

PAGE 61

MG-TAA component and equipment markers
Self-adhesive precut blank labels
Description–– To be used for external marking of components and equipment,–– Direct application on suitable surfaces (self-adhesive),–– Made of rigid PVC.

1SNC160139F0014

Main technical data

MG-TAA

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm
7 x 208 x 178.5 x 30

Nb. ofColormarkers
per card
in
0.276 x 0.787 60
0.315 x 0.669 72
0.335 x 1.181 33

9 x 159 x 209 x 3515 x 270.354 x 0.591
0.354 x 0.787
0.354 x 1.378
0.591 x 1.063

15 x 44
15 x 49

0.591 x 1.732 12
0.591 x 1.929 14

15 x 67

0.591 x 2.638 7

17 x 35

0.669 x 1.378 18

77
55
33
28

Type

Part Number

SW
code

Pkg

MG-TAA 49196
MG-TAA 49493
MG-TAA 49498
MG-TAA 49448
MG-TAA 49397N
MG-TAA 49190N
MG-TAA 49191N
MG-TAA 49193N
MG-TAA 49143N
MG-TAA 49298
MG-TAA 49194N
MG-TAA 49144N
MG-TAA 49195N
MG-TAA 49145N
MG-TAA 49198
MG-TAA 49148

1SNB049196R0720 179
1SNB049493R0817 194
1SNB049498R8530 720
1SNB049448R8530 720
1SNB049397R0915 961
1SNB049190N0920 962
1SNB049191R0935 964
1SNB049193R1527 966
1SNB049143R1527 966
1SNB049298R1544 854
1SNB049194R1549 967
1SNB049144R1549 967
1SNB049195R1567 968
1SNB049145R1567 968
1SNB049198R1735 711
1SNB049148R1735 711

1500
1800
825
825
1925
1375
825
700
700
300
350
350
175
175
450
450

MG2-PLT 991002

1SNB991002R0000

1

Weightmarker (1 marker) g

White
White
White
Yellow
White
White
White
White
YellowWhite
White
YellowWhite
YellowWhite
Yellow

0.30
0.30
0.55
0.55
0.30
0.40
0.60
0.70
0.70
1.20
1.40
1.50
2.80
2.80
0.91
0.91

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

148.50

Mounting instruction
AF09 contactor with MG-TAA 49196 marker

Compatible holders

LH(only for MG-TAA 49498 and 49448)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

LH-R1(only for MG-TAA 49198 and 49148)

PEB(only for MG-TAA 49198 and 49148)

1SNC160179S0201 - Rev. B

3

Material
Rigid PVC

MG-VYT component and equipment markers
Self-adhesive precut blank labels
Description–– To be used for external or internal marking of components and equipment,–– Direct application on suitable surfaces (self-adhesive),–– Made of dielectric PVC film.

MG-VYT 46915

Material
Dielectric PVC film

Flammability
V0

Temperature range-40°C to +80°C -40°F to +176°F

Ordering details
Dimensionsmmin

For internal marking
6 x 150.236 x 0.591

Nb. ofColormarkers
per card
105

7 x 107 x 157 x 208 x 21
9 x 150.276 x 0.394
0.276 x 0.591
0.276 x 0.787
0.315 x 0.827
0.354 x 0.591

12060

9 x 200.354 x 0.787

5570

9 x 350.354 x 1.378 33
For external marking
52 x 107
2.047 x 4.213 2
For Allen Bradley internal marking
5 x 120.197 x 0.472 120
For Telemecanique
8 x 170.315 x 0.669 72
For Telemecanique internal marking
8 x 170.315 x 0.669 72

TypePart Number

SW
code

Pkg

Weightmarker (1 marker) g

White
Yellow
Grey
Grey
Grey
White
Grey
White
Yellow
White
Grey
White

MG-VYT 46915
MG-VYT 46415
MG-VYT 46815
MG-VYT 46891
MG-VYT 46828
MG-VYT 46935
MG-VYT 46824
MG-VYT 44895
MG-VYT 44845
MG-VYT 44896N
MG-VYT 46896N
MG-VYT 46910N

1SNB046915R0615
1SNB046415R0615
1SNB046815R0615
1SNB046891R0710
1SNB046828R0715
1SNB046935R0720
1SNB046824R0821
1SNB044895R0915
1SNB044845R0915
1SNB044896R0920
1SNB046896R0920
1SNB046910R0935

181
181
181
191
182
179
196
161
161
162
162
164

5250
5250
5250
6000
3000
3000
3000
3500
3500
2750
2750
1650

0.10

Grey

MG-VYT 46811

1SNB046811R0052 204

100

2.40

White

MG-VYT 46927

1SNB046927R0512 195

6000

Yellow

MG-VYT 46423

1SNB046423R0817 194

3600

0.10

White
Grey

MG-VYT 46923
MG-VYT 46823

1SNB046923R0817 194
1SNB046823R0817 194

3600
3600

0.10
0.10

MG2-PLT 991002

1SNB991002R0000

1

0.10
0.10
0.10
0.10
0.10
0.10
0.10
0.10
0.10

3

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

148.50

Mounting instruction
AF09 contactor with MG-VYT 46935 marker

1SNC160181S0201

1SNC160140F0014

Main technical data

PAGE 63

MG-17.5A component and equipment markers
Self-adhesive precut blank labels

1SNC160265F0014

Description

MG-17.5-A 990824–– Used for marking modular components,–– Direct application on suitable surfaces (self-adhesive),–– Made of rigid PVC.

Main technical data
Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm
15 x 107.5

Nb. ofColormarkers
per card
in
0.591 x 4.232 7

TypePart Number

SW
code

Pkg

Weight

MG-17.5-A 990824
MG-17.5-A 990826

1SNB990824R0015 929
1SNB990826R0015 929

175
175

2.80
1.00

MG2-PLT 991002

1SNB991002R0000

1

148.50marker (1 marker) g

White
Yellow

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

Mounting instruction

1SNC160183S0201 - Rev. C

3

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

MG-PTS component and equipment markers
Precut blank labels
Description

1SNC160136F0014–– To be used for Ø 22.5 mm 0.886 in or Ø 31 mm 1.220 in push buttons identification,–– Direct application on suitable surfaces,–– Made of rigid PVC.

Main technical data
Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

MG-PTS 15090

Ordering details
Dimensionsmm
40 x 30

Nb. ofColormarkers
per card
in1.575 x 1.181 6

TypePart Number

SW
code

Pkg

Weight

MG-PTS 15090

1SNB015090R4030 1000

300

1.40

MG2-PLT 991002

1SNB991002R0000

1

148.50marker (1 marker) g

WhiteMarking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

3

1SNC160184S0201 - Rev. A

Mounting instruction

PAGE 65

MG-TAP component and equipment markers
Precut blank labels
Description–– Versatile precut label used to identify a wide range of devices : modular, component, push button, etc.,–– Can be used with legend rail RTA-TAP,–– Made of rigid PVC.

1SNC160134F0014

Main technical data

MG-TAP

Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

SW
code

Pkg

Weightmarker (1 marker) g

8.2 mm 0.323 in width
8.2 x 27

0.323 x 1.063 44

White

MG-TAP 47096

1SNB047096R0827 807

2200

0.30

White
Yellow
White
White
White

MG-TAP 47091N
MG-TAP 47041N
MG-TAP 47198
MG-TAP 47092N
MG-TAP 47093N

1SNB047091R1527
1SNB047041R1527
1SNB047198R1543
1SNB047092R1549
1SNB047093R1567

166
166
353
167
168

1400
1400
700
700
350

0.40
0.50
0.10
0.90
1.80

White
Yellow

MG-TAP 47097
MG-TAP 47047

1SNB047097R1827 178
1SNB047047R1827 178

1000
1000

0.60
0.60

MG2-PLT 991002

1SNB991002R0000

1

15 mm 0.591 in width
0.591 x 1.063 28

15 x 43
15 x 49
15 x 67

0.591 x 1.693 14
0.591 x 1.929
0.591 x 2.638 7

18 mm 0.709 in width
18 x 270.709 x 1.063 20

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

148.50Compatible holders

RTR-TAP 990454 and 990452
Pre-drilled rails (only for 15 mm 0.591 in MG-TAP)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRTA-TAP 990455N and 990453N
Self-adhesive rails (only for 15 mm 0.591 in MG-TAP)

1SNC160176S0201

3

15 x 27

RT... rail marker holders & protective covers
For MG-TAP labels

RTR-TAP–– Provide an alternative to direct marking on components,–– Compatible with MG-TAP labels with a width of 15 mm (0.591 in),–– Non-deformable up to 90°C, resistant to acid, alcohol, solvents,–– Made of rigid dielectric high-impact PVC .

Main technical data
Material
Rigid dielectric high-impact PVC

Flammability
V0

Temperature range+10°C to + 40°C +50°F to +104°F

Ordering details
Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightpce(1 pce) g

RTR-TAP
Pre-drilled rail
15 x 430 0.591 x 16.929

Black
Grey

RTR-TAP 990454
RTR-TAP 990452

1SNB990454R0000
1SNB990452R0000

25
25

37.60
0.50

Black
Grey

RTA-TAP 990455N
RTA-TAP 990453N

1SNB990455R0000
1SNB990453R0000

25
25

19.50
0.50

RT-CCP 990456

1SNB990456R0000

25

12.60

RTA-TAP
Self-adhesive rail
15 x 430 0.591 x 16.929

3

RT-CCP
Protective cover
15 x 430 0.591 x 16.929

Transparent

1SNC160222S0201

1SNC700114F0000

Description

PAGE 67

MG-TAPW component and equipment markers
Precut blank labels
Description–– 9 mm 0.354 in width versatile label used to identify a wide range of devices,–– Use with label rail holders RTA-TAPW 990653N,–– Made of rigid PVC.

1SNC160137F0014

Main technical data

MG-TAPW

Material
Rigid PVC

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensions

3

Flammability
V0mm
9 x 129 x 15

Nb. ofColormarkers
per card
in
0.354 x 0.472 88
0.354 x 0.591 77

9 x 200.354 x 0.787 55

9 x 290.354 x 1.142 30

9 x 350.354 x 1.378 33

TypePart Number

SW
code

MG-TAPW 49042N
MG-TAPW 49093N
MG-TAPW 49043N
MG-TAPW 49090N
MG-TAPW 49040N
MG-TAPW 49096
MG-TAPW 49046
MG-TAPW 49091N

1SNB049042R0912
1SNB049093R0915
1SNB049043R0915
1SNB049090R0920
1SNB049040R0920
1SNB049096R0929
1SNB049046R0929
1SNB049091R0935

360
361
361
362
362
363
363
364

MG2-PLT 991002

1SNB991002R0000

Pkg

Weightmarker (1 marker) g

YellowWhite
YellowWhite
YellowWhite
Yellow
White

2200
1925
1925
2750
2750
1500
1500
1650

0.10
0.20
0.20
0.20
0.60
0.30
0.30
0.40

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

1148.50Pkg

Weightpce(1 pce) g

25

47.50

Compatible holders

PEAD(only for MG-TAPW 49096 and 49046)

1SNC700116F0000

RTA-TAPW self-adhesive rail marker holders
For MG-TAPW labels
Description–– Provide an alternative to direct marking on components,–– Compatible with 9 mm 0.354 in MG-TAPW labels,–– Non-deformable up to 90°C, resistant to acid, alcohol, solvents.

RTA-TAPW

Main technical data
Material
Rigid dielectric high-impact PVC

Flammability
V0

Temperature range+10°C to + 40°C +50°F to +104°F

Dimensions
mmin

Nb. ofColormarkers
per card

Type

Part Number

RTA-TAPW
Self-adhesive rail
9 x 430
0.354 x 16.929

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSGrey

RTA-TAPW 990653N

1SNB990653R0000

1SNC160177S0201

Ordering details

MG-TAP-CCS component and equipment markers
Precut transparent labels
Description

MG-TAP-CCS

Main technical data
Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm
15 x 49
15 x 67

Nb. ofColormarkers
per card
in
0.591 x 1.929 12
Transparent
0.591 x 2.638 6Transparent

TypePart Number

SW
code

Pkg

Weightmarker (1 marker) g

MG-TAP-CCS 990513 1SNB990513R1549 167
MG-TAP-CCS 990514 1SNB990514R1567 168

600
300

0.90
1.30

Marking system accessories

3

MG2-PLT
Support plate
Included in the MG3 Kit

MG2-PLT 991002

1SNB991002R0000

1

148.50

Mounting instruction
MG-TAP-CCS
MG-TAP

Compatible holders

RTR-TAP 990454 and 990452
Pre-drilled rails

1SNC160178S0201

1SNC160135F0014–– To be directly printed,–– Can also be used as a protective cover with 15 mm 0.591 in MG-TAP or MG-TAPW labels and 15 mm
0.591 in RTR-TAP and RTA-TAP legend rails,–– Made of rigid PVC.

RTA-TAP 990455N and 990453N
Self-adhesive rails

PAGE 69

MG-TAR component and equipment markers
Precut blank labels
Description–– Designed to fit particular components with a suitable clip-in location,–– Made of rigid PVC.

1SNC160138F0014

Main technical data

MG-TAR 45194

Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm
17 x 35
17 x 44

Nb. ofColormarkers
per card
in
0.669 x 1.378 18
0.669 x 1.732 12

TypePart Number

SW
code

Pkg

WeightMG-TAR 45194
MG-TAR 45195

1SNB045194R1735 711
1SNB045195R1744 717

900
600

0.60
0.90

MG2-PLT 991002

1SNB991002R0000

1

148.50marker (1 marker) g

White
White

Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

Compatible holders

PEB(only for MG-TAR 45194)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

LH-R1(only for MG-TAR 45194)

1SNC160175S0201

3

MG-PLC component and equipment markers
Precut blank labels
Description

MG-PLC 71092

Main technical data
Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm
12.7 x 50

Nb. ofColormarkers
per card
in0.500 x 1.969 14

17.5 x 103.5

0.689 x 4.075 6

22.75 x 103.5 0.896 x 4.075 4

25 x 50

0.984 x 1.969 8

White
Yellow
Siemens Green
Grey
White
Yellow
Siemens Green
Grey
White
Yellow
Siemens Green
Grey
White
Yellow

TypePart Number

SW
code

Pkg

WeightMG-PLC 71092
MG-PLC 71042
MG-PLC 71052
MG-PLC 71002
MG-PLC 71090
MG-PLC 71040
MG-PLC 71050
MG-PLC 71000
MG-PLC 71091
MG-PLC 71041
MG-PLC 71051
MG-PLC 71001
MG-PLC 71094
MG-PLC 71044

1SNB071092R0012
1SNB071042R0012
1SNB071052R0012
1SNB071002R0012
1SNB071090R0017
1SNB071040R0017
1SNB071050R0017
1SNB071000R0017
1SNB071091R0022
1SNB071041R0022
1SNB071051R0022
1SNB071001R0022
1SNB071094R0025
1SNB071044R0025

884/886
884/886
884/886
884/886
880
880
880
880
883
883
883
883
887/888
887/888

700
700
700
700
300
300
300
300
200
200
200
200
400
400

0.40
0.50
0.80
0.40
2.20
2.00
2.20
1.00
2.90
2.80
3.00
1.00
1.00
0.90

1

148.50marker (1 marker) g

3Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

MG2-PLT 991002 1SNB991002R0000

Mounting instruction

1SNC160182S0201

1SNC160141F0014–– To be used for PLC's marking,–– Direct application on PLC to replace the neutral plates supplied as original equipment,–– Made of rigid PVC.

PAGE 71

MG-VRT-A panel plates
Self-adhesive blank panel plates
Description–– To be used in identifying panels and cabinets with technical data or logos,–– Made of rigid PVC.

1SNC160143F0014

Main technical data

MG-VRT-A 88903

Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm

Nb. ofColormarkers
per cardin

TypePart Number

SW
code

Pkg

Weightmarker (1 marker) g

Self-adhesive panel plate for direct application on suitable surfaces
52 x 107
2.047 x 4.213 2
White
MG-VRT-A 88903

1SNB088903R0052 204

50

9.90

1SNB991002R0000

1

148.50Pkg

WeightMarking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

MG2-PLT 991002

3

MG-VRT-R panel plates
Blank panel plates
Description–– To be used in identifying panels and cabinets with technical data or logos,–– To be fixed with rivets,–– Made of rigid PVC.

1SNC160144F0014

Main technical data

MG-VRT-R 48903

Material
Rigid PVC

Flammability
V0

Temperature range-30°C to +80°C -22°F to +176°F

Ordering details
Dimensionsmm

Nb. ofColormarkers
per cardin

TypePart Number

SW
code

marker (1 marker) g

Rivet fixing panel plate
52 x 107
2.047 x 4.213 2

White

MG-VRT-R 48903

1SNB048903R0052 204

100

6.40

MG2-PLT 991002

1SNB991002R0000

1

148.50Marking system accessories
MG2-PLT
Support plate
Included in the MG3 Kit

Mounting instruction

1SNC160185S0201 - Rev. A

40 1.57"

90 3.54"

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

PB75

3

PAGE 73

Summary_4

4

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSSolution series
Blank markers and labels for AMS 600 and AMS 250 plotter

AMS 600 and AMS 250 plotter

76

AMS kit and accessories

78

Terminal block identification
Selection guide for terminal block markers
Terminal block markers

80
MC…PA

for SNK series

82

RC…10

for SNA and Solution series

83

RC55, RC65, RCAL85

for SNA and Solution series

84

RCT…

for top marking

RB-12W7		

End stop markers

End stop label holders and covers

85
86

RPEV

for PEV label holder

87

RTM7

strip labels

88

REH3

for Solution series

MCLH, MCLH-R1		

89
90

RCPEAD		92

RPEH		

93

RCPEB, PIB, PIB3		

94

LH, LH-R1

for SNK series

91

PEAD, EPR2

for SNA and Solution series

92

PEB, PEBM, EPR1

for SNA and Solution series

95

WM

PVC label (need label holder)

98

PCGS

large label (need label holder)

100

RING, SNAP, RINGT23

transparent label holder

99

RINGT209

for large label tied-on thick cables

100

4

Wire and cable identification
Selection guide for wire and cable markers
Wire and cable markers
Wire and cables label holders

96

Component and equipment identification
Self-adhesive labels

Pre-cut labels
Label holders and covers

RPA, PIB2		

102

PSP

for engraving job

PAM

for strip identification

104

BA4

for contactors, relays...

105

PPB

two-colored label

106

PAM10015,PCT

15 mm rail and protective cover107

KA1-8120

push-button marker holder

107

103

Panel identification
PAT		

108

Rivet fixing panel plates

PPT		

108

Summary_4

Self-adhesive panel plates

PAGE 75

AMS 600 and AMS 250 plotter
The universal standard for printing jobs

AMS 600
Universal printing plotter
Compatible with all original manufacturer terminal block markers (polyamide), it can also print other identification supports
such as: wire and cable markers, push buttons, panels…
This plotter offers a large working area, hosting up to 4 different support plates for one plot job.
Error detection mode
The A3 panel automatically recognises the support plate andavoids the need to select marking elements, it also warns theuser when the support is wrongly installed.
Dry out protection system
Pens are prevented from drying out thanks to AMS 600 integrated pen station.

4

AMS 250

1SNC160215S0201

Compact
This A4 plotter is smaller than AMS 600 and is more suited toa cluttered environment.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSAutomatic installation
The installation program starts automatically. The computer
just needs to be rebooted after it has finished and printing canstart.

Microsoft, Windows, Excel are trademarks of Microsoft Corporation.

What you see is what you get !

User friendly
Microsoft® Windows® software

4Time saving: data import function
from CAD, TXT and Excel® files

1SNC160215S0201

New special ink disposable plotter pens ED-R–– Disposable pens ED-R almost never clog, they are ideal foruse in particularly dry environments.
–– These pens are filled with the permanent ink ED, most suitable for marking various plastic surfaces.
–– The ED ink should only be used on plastic material. Do notclean or touch with aggressive fluids.
–– For applications outside of the control panel the ink P 2.0
is more suitable and durable.

PAGE 77

AMS plotter
Kit and accessories

AMS 600
Description–– For basic marking applications,–– Economic,–– Full-size format,–– Print original manufacturers' markers.
AMS 600

Ordering details
Description

Color

AMS 600 Plotter KIT
List of items included in the KIT:
1 AMS 600 plotter pen printer1 Software CD
1 Power supply cable
1 USB cable
1 Support plate for RC / MC / RCTT / WMTT /BA4 / RCT
1 Support plate for MC...PA
1 Plotter pen Ø 0.25 mm .01 in
1 Plotter pen Ø 0.35 mm .014 in
5 Ink cartridges
1 Cleaner fluid
1 Cleaner kit

Type
AMS 600 KIT

Pkg

Weightpce(1 pce) g

1SNA360000R2400

1

12600

Part Number

Pkg

Weightpce(1 pce) g

Part Number

AMS 600AMS SOFTWAREAMS POWERAMS USB
SPRC1
SPRC 30-3
AMS PEN 0.25
AMS PEN 0.35
AMS INK CARTRIDGESAMS CLEANER FLUIDAMS CLEANER KIT

4

AMS 250
Description–– Basic needs,–– Economic,–– Half-size format–– Compatible with most of AMS 600 accessories.
AMS 250

Ordering details
Description

Type
AMS 250 BASIC KIT

1SNA360000R2500

1

8800

AMS 250 BASICAMS SOFTWAREAMS POWERAMS USBSPRC2DISPOSABLE AMS PEN
ED-R 0.25
DISPOSABLE AMS PEN
ED-R 0.35

1SNC160110S0201

AMS 250 Plotter KIT
List of items included in the KIT:
1 AMS 250 plotter pen printer1 Software CD
1 Power supply cable
1 USB cable
1 Support plate for BA4 / MC / RC / RCAL /RCT / RCTT
1 Disposable plotter penØ 0.25 mm .01 in EDR ink
1 Disposable plotter penØ 0.35 mm .014 in EDR ink

Color

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSAMS plotter
Kit and accessories
Support plates for TE Connectivity markers
Description

Compatibility
AMS 500
AMS 600

Type

Pkg

Weightpce(1 pce)

1SNA360010R1500
1SNA360011R1500
1SNA360014R0500
1SNA360015R0600
1SNA360023R0600
1SNA360024R0700
1SNA360025R0000
1SNA360026R0100
1SNA360036R0300
1SNA360037R0400
1SNA360040R2300
1SNA360038R1500
1SNA360039R1700
1SNA360031R0600

1
1
1
1
1
1
1
1
1
1
1
1
1
1

1500.00
600.00300.001700.00
260.00300.00300.00300.00300.00300.00300.00300.00500.00500.00Part Number

Pkg

Weightpce(1 pce)Part Number

AMS 250g

Support plates for:

SPRC1

RC/MC/RCTT/WMTT/BA4/RCT full format
RC/MC/RCTT/WMTT/BA4/RCTRB strips
RTM7-9PIB
BA5-50
RC-X10A
2 RC cards
WM markers
PAM strip
RPCV markers
RCL, P, W510
MC... PA

A4 universal support plate
SPRC2




























SPRC 1SPRC 2SPRC 4SPRC 5SPRC 13SPRC 14SPRC 15SPRC 16SPRC 26
SPRC 27
SPRC 28
SPRC 29
SPRC 30-3
SPRC 21

Support plates for other manufacturers
Description
Support plates for markers:
WielandWeidmüller
Phoenix ZBM 5/6
Phoenix ZB
Allen Bradley WRZ
Wago mini WSB5

Compatibility
AMS 500
AMS 600

AMS 250















Type

SPRC 6SPRC 7SPRC 8SPRC 9SPRC 10SPRC 11

1SNA360016R0700
1SNA360017R0000
1SNA360018R1100
1SNA360019R1200
1SNA360020R1700
1SNA360021R0400

TypePart Number

1
1
1
1
1
1

g

350.00400.00300.00300.00330.00300.004

SPRC30-3

Accessories

AMS PENAMS CLEANER KIT

Diameter
Color

Plotter pen P 2.0 black ink Ø 0.18 mm 0.007 inØ 0.25 mm 0.01 inØ 0.35 mm 0.014 inØ 0.50 mm 0.02 inØ 0.70 mm 0.028 inØ 1.00 mm 0.039 in
Disposable plotter penØ 0.25 mm 0.01 in
P 2.0 black ink
Ø 0.35 mm 0.014 in
Disposable plotter penØ 0.18 mm 0.007 in
ED-R black ink
Ø 0.25 mm 0.01 in

OrangeØ 0.35 mm 0.014 inYellow

5 ink cartridges 1 ml
2 cleaner fluid bottles, 2x10 ml
Cleaner kit including: 1 rinse bottle and 1 blotting paper
Dust coverService kit for pen maintenanceSelf-adhesive support for support plate SPRC 1
Plotter head for AMS 600 including 1 printing
module, 1 pen holder and 1 dust cover

Red
White
Yellow
Brown
Blue
White
Yellow
Red
White

Pkg
1
1
1
1
1
1
1
1
1

Weight
g
15.00
15.00
15.00
26.00
26.00
26.00
24.00
24.00
24.00

1

24.00

1

24.00

1
1
1
1
1
1
1

18.00
40.00
34.00
200.00
12.00
70.00
85.00

pce

AMS PEN 0.18
1SNA360103R1400
AMS PEN 0.25
1SNA360100R2500
AMS PEN 0.35
1SNA360101R1200
AMS PEN 0.50
1SNA360104R1500
AMS PEN 0.70
1SNA360105R1600
AMS PEN 1.00
1SNA360106R1700
DISPOSABLE AMS PEN 0.25 1SNA360120R1000DISPOSABLE AMS PEN 0.35 1SNA360121R0500
DISPOSABLE AMS PEN
1SNA360124R1000
ED-R 0.18
DISPOSABLE AMS PEN
1SNA360122R1000
ED-R 0.25
DISPOSABLE AMS PEN
1SNA360123R0500
ED-R 0.35
AMS INK CARTRIDGES
1SNA360150R2600
AMS CLEANER FLUID
1SNA360155R1700
AMS CLEANER KIT
1SNA360156R1000
DUST COVER
1SNA360161R1500
SERVICE KIT FOR AMS 600 1SNA360162R1600
SPDST1
1SNA360163R1700
PEN HOLDER
1SNA360098R1200(1 pce)1SNC160111S0201 - Rev. A

Description

AMS INK CARTRIDGESPAGE 79AMS 600 / AMS 250 markers selection guide
Terminal block blank markers selection guide
Terminal blocks
Connection technology

Terminal block part number

Marker typeMarker mounting

Screw clamp

1SNK...

Individual
markerTop and side marking

1SNA...

Side marking

Individual
marker

Top marking

Strip label

Top marking

1SNA...
Miniblocks (MS...)

Individual
markerSide marking

1SNA...
Miniblocks (DR...)

Individual
markerSide marking

PI-Spring andpluggable PI‑Spring

1SNK...

Individual
markerTop and side marking

Spring clamp

1SNA...

1SNA...
Miniblocks
ADO System®

Side marking

Individual
marker

1SNA...

Top and side marking
Side marking

Individual
marker4

1SNA...
Miniblocks
Spring loaded
screw clamp

Top marking

Individual
marker

1SNA...

Top marking

Strip label

Top marking

Individual
marker

Top marking
Side marking

Individual
marker

Top marking

Strip label

Top marking

Special terminal blocks spacing
Connection technology

Terminal blockMarker typeMarker mounting

Ring lug

1SNA...

Individual
markerTop and side marking

Stud

1SNA...

Individual
markerTop and side marking

Screw clamp
pluggable
terminal block

1SNA...

Individual
markerSide marking

Strip label

Top marking(MA2.5/5-CPE)

SNK series end stop and label holders
BAZ1

Individual
marker

BAM4
LH (label holder for BAM4, BAZH1, BAZ1)

Label

LH-R1 (label holder for BAM4, BAZH1, BAZ1)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

Top marking

MC512PATop and sidemarking

MC812PATop marking

MC-LH
MC-LHR1

Spacing
4 mm
0.157 in

5 mm
0.197 in

5.2 mm0.205 in

6 mm
0.236 in

8 mm
0.315 in

MC512PAMC612PAMC812PA

RC510

RC610

RC810

RC510

RCT610

RCT810

RTM9

RC410

12 mm
0.472 in

16 mm
0.630 in

22 mm
0.866 in

26 mm
1.024 in

31 mm
1.220 in

36 mm
1.417 in

MC812PA (1)RC1010RC1010 (1)

RTM7
RC610

RC810

RC65

RC810

MC612PAMC812PA

RC510

RC610

RC810

RC55

RC65

RC55
MC512PA

RC410

10 mm
0.394 in

MC812PA (1)RC1010RC1010 (1)RCAL85

RC55

RC55

RC510

RC610

RC810

RCT610

RCT810

4

RTM7
RC55

RC65

RCAL85

RC610

RC810

RCT610

RCT810RC1010RTM9(1) Marker width < marking's area size - markers must be mounted individually.

Spacing
5.08 mm

7.62 mm

9.5 mm0.200 in

0.300 in

0.374 in12.5 mm

13 mm

16 mm

26 mm

27 mm

31 mm

32 mm

35 mm

42 mm

55 mm

0.492 in

0.512 in

0.630 in1.024 in1.063 in

1.220 in

1.260 in

1.378 in

1.654 in2.165 in

RC1010 /
REH3

REH3
PEP +
RC610

RC810 (1)

PEP +
RC610

RC810 (1)

PEP +
RC610

RCT810

RC510

RC810 (power) RC810 (1)PEP+RC610 (stud)RB-12W7

RTM7(1) Marker width < marking's area size - markers must be mounted individually.

SNA series end stop and label holders
BADL
BADRL, BAR
BAMHPEAD (Label holder for BAM2 and BADL)

Individual
markerTop and sidemarking

RC1010Individual
marker

Top marking

RC610

Label

Top marking

RC810

1SNC160216S0201

BAM2, BADH

RC1010RCPEADPEB (Label holder for BAM2, BADL, BADH, BAMH, BAR and BADRL)PIBPEH (Label holder for BAM2, BADL, BADH, BAMH, BAR and BADRL)

RPEH

PAGE 811SNK160024F0014

MC..PA terminal block markers
Blank markers for SNK series

MC512PA

Description–– Blank marker card in polyamide,–– Terminal blocks are directly independent after strip mounting,–– Improved marking visibility thanks to the increased marking surface +20% (12 mm 0.472 in).

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

For 5.2 mm 0.205 in spacing
MC512PA
12 x 50.472 x 0.197 3

8

100

White

MC512PA1SNK149999R0000

20

10.00

100

White

MC612PA1SNK159999R0000

20

11.00

100

White

MC812PA1SNK169999R0000

20

14.00

SPRC 30-3

1SNA360039R1700

1

500.00For 6 mm 0.236 in spacing
MC612PA
12 x 5.6 0.472 x 0.220 38

For 8 mm 0.315 in spacing
MC812PA
12 x 7.6 0.472 x 0.299 48Marking system accessories
SPRC 30-3
Support plate for AMS600 and AMS250
Included in KIT MAO AMS 600 only

Mounting instruction

1SNC160133S0201

4

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC..10 terminal block markers
Blank markers for SNA and solution series

RC510–– Blank card in polyamide,–– Terminal blocks are directly independent after strip mounting,–– To be used to mark spring clamp, ADO System® and screw clamp pluggable SNA terminal blocks.

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

For 4 mm 0.157 in terminal block spacing
RC410
10 x 40.394 x 0.157 2

7

100

White

RC410

1SNA229000R1500

10

5.20

RC510
RC510-YL

1SNA231000R0700
1SNA103890R2100

10
10

5.20
5.50

RC610
RC610
RC610
RC610
RC610
RC610

1SNA233000R0100
1SNA206233R0000
1SNA206232R0700
1SNA206231R0600
1SNA206230R1100
1SNA206235R0200

10
10
10
10
10
10

6.70
6.70
6.70
6.70
6.70
6.70

RC810

1SNA234000R0200

10

8.20

RC1010

1SNA238000R1600

10

1.30

SPRC 1

1SNA360010R1500

1

1500.00

SPRC 2

1SNA360011R1500

1

600.00For 5 mm 0.197 in terminal block spacing
RC510
10 x 50.394 x 0.197 3
4

7
4

100

White
Yellow

For 6 mm 0.236 in terminal block spacing
RC610
10 x 6
0.394 x 0.236 4

4

100

White
Blue
OrangeYellow
Green
Red

4

For 8 mm 0.315 in terminal block spacing
RC810
10 x 80.394 x 0.315 4

4

100

White

For 10 mm 0.394 in terminal block spacing
RC101010 x 10 0.394 x 0.394 7

7

80

White

Marking system accessories
SPRC 1
Support plate for AMS600
Included in KIT MAO AMS 600
SPRC 2
Support plate for AMS250
Included in AMS 250 BASIC KITMounting instruction

1SNC160113S0201 - Rev. A

1SNC700141F0000

Description

PAGE 83

RC55, RC65, RCAL85 terminal block markers
Blank markers for SNA and Solution series

1SNC700141F0000

Description–– Blank card in polyamide,–– Terminal blocks are directly independent after strip mounting,–– To be used to mark screw clamp (1) and spring clamp (side mounting) SNA terminal blocks, and all Miniblocks.

RC55

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

For 5 mm 0.197 in terminal block spacing
RC55
5x5

0.197 x 0.197 3

3

100

White

RC55

1SNA230000R1200

10

2.90

RC65
RC65
RC65

1SNA232000R0000
1SNA103775R0000
1SNA103776R0100

10
10
10

3.60
3.40
3.40

RCAL85

1SNA237000R0500

10

2.90

SPRC 1

1SNA360010R1500

1

1500.00

SPRC 2

1SNA360011R1500

1

600.00For 6 mm 0.236 in terminal block spacing
RC65
5x6

3

100

White
Blue
Red

For 8 mm 0.315 in terminal block spacing (1)
RCAL855x80.197 x 0.315 5

3

100

White

Marking system accessories
SPRC 1
Support plate for AMS600
Included in KIT MAO AMS 600

SPRC 2
Support plate for AMS250
Included in AMS 250 BASIC KIT(1) RCAL85 not compatible with screw clamp terminal blocks

Mounting instruction

1SNC160114S0201 - Rev. A

40.197 x 0.236 3

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRCT.. terminal block markers
Blank markers for SNA and Solution series

1SNC700141F0000

Description–– Blank card in polyamide,–– Terminal blocks are directly independent after strip mounting,–– To be used for top marking of screw clamp and ADO System® terminal blocks from the SNA and Solution
series.

RCT610Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensionsmm

Nb. ofmarkers
per card

in

Color

Type

Part Number

Pkg

Weightcard(1 card) g

For 6 mm 0.236 in terminal block spacing
RCT61010 x 6

0.394 x 0.236

100

White

RCT610

1SNA236000R0400

10

6.40

RCT810

1SNA236500R0600

10

7.60

For 8 mm 0.315 in terminal block spacing
RCT81010 x 80.394 x 0.315

100

White

4

Marking system accessories
SPRC 1
Support plate for AMS600
Included in KIT MAO AMS 600

SPRC 1

1SNA360010R1500

1

1500.00

SPRC 2

1SNA360011R1500

1

600.00SPRC 2
Support plate for AMS250
Included in AMS 250 BASIC KITMounting instruction

1SNC160115S0201 - Rev. A

Top marking

PAGE 85

RB-12W7 terminal block markers
Blank strip markers for SNA and Solution series

1SNC700164F0000

Description

RB-12W7–– Blank marking strip,–– Strip of 12 markers available in pre-printed on request,–– To be used for top marking of ADO System® pluggable terminal blocks.

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensionsmmin

RB-12W7
3.6 x 7.62 0.141 x 0.300

Nb. ofmarkers
per card

Color

12

Type

White

Part Number

Pkg

Weightcard(1 card) g

RB-12W7

1SNA290455R0700

50

6.00

SPRC 4

1SNA360014R0500

1

300.00Marking system accessories
SPRC 4
Support plate for AMS600 and AMS250
Purchased separately

4

Mounting instruction

1SNC160118S0201

Strip marking

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC700163F0000

RPEV terminal block markers
Precut blank labels for SNA and Solution series

RPEV

Description–– Precut PVC label,–– To be used with PEV pivoting marker holder.

Main technical data
Material
PVC

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

RPEV
6 x 290.236 x 1.142

99

Color

Type

White

Part Number

Pkg

Weightcard(1 card) g

RPEV

1SNA173178R0700

1

9.20

SPRC 21

1SNA360031R0600

1

500.00Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

PEV pivoting terminal block marker holders
For RPEV markers

4

Description

Material

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

10

1.00

PEV
Pivoting marker holder
6 x 290.236 x 1.142

Grey

PEV

1SNA113180R1200

Dimensions given apply to the labelling area.

Mounting instruction

29 1.14"

1 - For 6 mm (0.236 in) and
8 mm (0.315 in) spacing
terminal blocks : PEV can beused on every other block
2 - From 10 mm (0.394 in)spacing terminal blocks : PEV
can be used side by side
1SNC160119S0201(2)
8 0.31"(1)

6 0.24"PEV

Main technical data

6 0.24"1SNC160192F0014–– To be slided into 6 mm 0.236 in spacing terminal blocks,–– Can be placed side by side from 10 mm 0.394 in spacing,–– The pivoting upper part provides access to the compression screws,–– Designed to be mounted individually.

PAGE 87

RTM terminal block markers
Blank strip labels for SNA and Solution series

1SNC700180F0000

Description

RTM7–– Blank marking strip,–– To be top mounted by sliding it in terminal blocks.

Main technical data
Material
PVC

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

RTM7
For screw clamp and ADO System® terminal blocks from the SNA and Solution series, 6 mm 0.236 in to 12 mm 0.472 in
spacing
7.6 x 500 0.299 x 19.685 1
White
RTM7
1SNA168410R0700
1

5.00

RTM9
For terminal blocks type MA 2.5/5 and M 35/16
10 x 500
0.394 x 19.685 1

White

RTM9

1SNA164602R0000

1

5.00

SPRC 5

1SNA360015R0600

1

1700.00

Marking system accessories
SPRC 5
Support plate for AMS600
Purchased separately

Mounting instruction

1SNC160117S0201

4

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSREH3

Description–– Precut blank labels in cellulose acetate,–– Terminal blocks are directly independent after mounting,–– To be used to mark 13 mm 0.512 in or 16 mm 0.630 in spacing ring lug terminal blocks from the Solution
series.

Main technical data
Material
Cellulose Acetate

Flammability
V2

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

REH3
7x5

0.276 x 0.197

680

Color

Type

White

Part Number

Pkg

Weightcard(1 card) g

REH3

1SNA163155R2600

1

20.00

SPRC 21

1SNA360031R0600

1

500.00Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

4

1SNC160116S0201

1SNC700160F0000

REH3 terminal block markers
Precut blank labels for Solution series

PAGE 89

MCLH end stop markers
Self-adhesive precut blank labels for SNK series

1SNC700301F0000

Description

MCLH, MCLH-R1–– Identify your terminal blocks assembly with the self-adhesive label adapted to the LH label holders.

Main technical data
Material
PVC + Adhesive acrylic

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensionsmm

Nb. ofmarkers
per card

in

Color

Type

Part Number

Pkg

Weightcard(1 card) g

For LH label holder
MCLH
30 x 8.8

1.181 x 0.346

36

White
Yellow

MCLH
MCLH-YL

1SNK900630R0000
1SNK900633R0000

25
25

10.00
10.00

White
Yellow

MCLH-R1
MCLH-R1-YL

1SNK900631R0000
1SNK900634R0000

25
25

10.00
10.00

SPRC 21

1SNA360031R0600

1

500.00For LH-R1 label holder
MCLH-R1
35.35 x1.392 x 0.695
17.65Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

Mounting instruction

MCLH

8.8
0.346"

30 1.18"

MCLH-R1

17.65 0.695"

35.35 1.39"

Compatible holders

LH

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

LH-R1

1SNC160128S0201

4

15

LH, LH-R1 end stop label holders
For MCLH labels
Description

1SNK160210F0014–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with all SNK end stops.

Main technical data
Material
Polyamide

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Spacingmm

Dimensions
in

Color

Type

Part Number

Pkg

Weightpce(1 pce) gmm

in

8.8 x 30

0.35 x 1.18

Dark GreyLH

1SNK900605R0000

50

0.60

0.70 x 1.40

Dark Grey

LH-R1

1SNK900607R0000

50

1.10

For MCLH
LH
10

For MCLH-R1
LH-R1
19.5
0.768

LH-R1

17.9 x 35.65

Dimensions given apply to the labelling area.

4

Compatible end stops

BAM4
1SNK900001R0000

BAZ1
1SNK900002R0000

1SNC160129S0201

LH

0.394

BAZH1
1SNK900102R0000

PAGE 91

RCPEAD end stop labels
Precut blank labels

1SNC700232F0000

Description

RCPEAD–– Identify your terminal block assemblies with the self-adhesive label adapted to the PEAD label holders.

Main technical data
Material
PVC

Flammability

Ordering details
Dimensionsmm

Nb. ofmarkers
per cardin

RCPEAD
9 x 290.354 x 1.142

Color

40

Type

White

Part Number

Pkg

Weightcard(1 card) g

RCPEAD

1SNA399725R0600

1

5.00

SPRC 21

1SNA360031R0600

1

500.00Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

Mounting instruction
PEAD + RCPEAD

4PEAD end stop label holders
For RCPEAD label
Description–– Easily identify your terminal block assemblies with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with BAM2 and BADL SNA series end stops.

1SNC160058F0014

Main technical data

PEAD

Material
Polyamide

Flammability
V0

Ordering details
Dimensions
mm

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

1SNA399719R1000

20

0.78

1SNA399726R0700

1

4.00

in

PEAD
Label holder for end stop, compatible with RCPEAD marker and EPR2 cover.
9 x 290.354 x 1.142
Grey
PEAD
EPR2
Card of 20 covers for RCPEAD and RCPEAD-TT markers
9 x 290.354 x 1.142
Transparent

EPR2

Compatible end stops

BAM2
1SNA206351R1600

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSBADL
1SNA399903R0200

1SNC160122S0201 - Rev. A

Dimensions given apply to the labelling area.

RPEH end stop labels
Precut blank labels

1SNC700308F0000

Description

RPEH–– Blank markers to be slided into PEH holders.

Main technical data
Material
PVC

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

1SNA163007R2600

1

20.00

1SNA360031R0600

1

500.00

RPEH
Precut markers to be slided into PEH 40 x 5 mm 1.575 x .197 in holders
5 x 400.197 x 1.575
120
White
RPEH

Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

SPRC 21

4

PEH end stop label holders
For RPEH
Description–– Compatible with marker PEH.

PEH

Material

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

10

382.00PEH
Horizontal label holder for end stop, to be attached accross end stop.
5 x 400.197 x 1.575
Transparent
PEH

1SNA163211R2600

Compatible end stops

BAM2
BADL
BADH
BAMH
BAR
BADRL
1SNA206351R1600 1SNA399903R0200 1SNA116900R2700 1SNA114836R0000 1SNA164519R2400 1SNA199420R2100

PAGE 93

1SNC160123S0201 - Rev. B

1SNC160260F0014

Main technical data

RCPEB, PIB, PIB3 end stop markers
Precut blank labels
Description

1SNC160200F0014–– Blank markers to be inserted onto PEB label holder,–– To be used for terminal block assembly identification.

RCPEB

Main technical data
Material
PVC

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

RCPEB
Card of 54 precut labels to be inserted onto PEB label holder
17.5 x 35 0.689 x 1.378
54
White
RCPEB

1SNA178430R0500

1

0.05

1SNA235462R2200

50

0.40

Individual labels to be inserted onto PEB label holder, white marking on black background17.5 x 35 0.689 x 1.378
1
Black
PIB
1SNA173812R1300

100

0.60

1

260.00PIB3
Strip of 7 labels to be inserted onto PEB label holder
17.5 x 35 0.689 x 1.378
7
White

PIB3

PIB

Marking system accessories
SPRC 13
Support plate for AMS600 and AMS250
Purchased separately

SPRC 13

1SNA360023R0600

Compatible holders

PEB

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160124S0201

4

PEB end stop label holders
For RCPEB, PIB, PIB3 labels
Description

PEB

Main technical data
Material
Polyamide (PEB)
PVC (EPR1)

Flammability
V0

Temperature range-55°C to +110°C -67°F to +230°F

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

50

1.70

PEB
Label holder for end stop 35 x 17 mm 1.378 x .669 in, to be snapped onto end stop
18 x 35.5
0.709 x 1.378
GreyPEB
1SNA113077R1100
EPR1
Card of 54 PVC protective covers
17.5 x 35
0.689 x 1.378

Transparent

EPR1

1SNA178431R2200

1

0.054

"All in one": PEB marker holder with marker and protection included
PEBM

1SNA113084R0100

50

2.80

PEBM

4

Compatible end stops

BAM2
BADL
BADH
BAMH
BAR
BADRL
1SNA206351R1600 1SNA399903R0200 1SNA116900R2700 1SNA114836R0000 1SNA164519R2400 1SNA199420R2100

PAGE 95

1SNC160125S0201 - Rev. A

1SNC160200F0014–– To be used for terminal block assembly identification,–– Direct insertion onto end stops from SNA series,–– Compatible with RCPEB, PIB, PIB3 labels.

AMS 600, AMS 250 wire and cable markers
Selection guide
Evolutive and protected wire andcable identification
Each individual label and label holder iseasily detached from the stem for installation onto cable. The printed label in its
holder is perfectly protected over time.

RING
Slide-on cable label holders
to be used before connecting
the wires.

SNAP
Clip-on cable label holders tobe snap-on the wire alreadyconnected or not.

RINGT
Tie-on cable label holders
recommended for thick tube,
hose and conduit.

1SNC160217S0201

4

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSAMS 600, AMS 250 wires and cables markers
Selection guide

For evolutive identification
Marker holders + slide-in markers

Wire external diameter
mm
in

RING

SNAP

Marker holder lengthmminMarker holder

Compatible marker

Slide-on cable marker holder
Ø 1.5 ... 2.5
Ø 0.059 ... 0.098
1218
Ø 2 ... 4
Ø 0.079 ... 0.157
1218
Ø 4 ... 7
Ø 0.157 ... 0.276
1218
Ø 6 ... 10Ø 0.236 ... 0.394
12
18

0.472
0.709
0.472
0.709
0.472
0.709
0.472
0.709

RING122
RING182
RING124
RING184
RING127
RING187
RING1210
RING1810

WM 12
WM 18
WM 12
WM 18
WM 12
WM 18
WM 12
WM 18

Clip-on cable marker holder
Ø 2 ... 3.5
Ø 0.079 ... 0.138
15
23
Ø 2.8 ... 5Ø 0.11 ... 0.197
1523
Ø 5 ... 8
Ø 0.197 ... 0.315
1523
Ø 8 ... 10Ø 0.315 ... 0.394
15
23

0.591
0.906
0.591
0.906
0.591
0.906
0.591
0.906

SNAP152
SNAP232
SNAP154
SNAP234
SNAP157
SNAP237
SNAP1510
SNAP2310

WM 12
WM 18
WM 12
WM 18
WM 12
WM 18
WM 12
WM 18

4

For identification of thick tubes
Tie-on markers / marker holders

RINGT23

Marker holder length
mm
in
23
23
28
28

Marker holder

Compatible marker

RINGT23
RINGT209

WM 18
PCGS209

1SNC160217S0201

RINGT209

PAGE 97

WM wire and cable markers
Slide-in precut blank labels

1SNC700182F0000

Description–– Blank marker card for wire and cable identification,–– Markers are protected in the marker holders,–– To be slided into RING or SNAP transparent holders,–– Made of ABS.

WM12

Main technical data
Material
Acrylonitrile Butadienne Styrene (ABS)

Flammability
V0

Temperature range-50°C to +80°C -58°F to +176°F

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

WM12
For 12 mm 0.472 in RING or SNAP holders
12 x 40.472 x 0.157 2
8
60

White

WM12

1SNA235148R0700

50

12.00

White

WM18

1SNA235149R0000

50

15.00

SPRC 26

1SNA360036R0300

1

300.00

WM18
For 18 mm 0.709 in RING or SNAP holders
18 x 40.709 x 0.157 2
1060Marking system accessories
SPRC 26
Support plate for AMS600 and AMS250
Purchased separately

Compatible holders

RING
Sealed transparent holder

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

SNAPUnsealed transparent holder

RINGT23
Tie-on sealed transparent holder

1SNC160120S0201

4

RING, SNAP transparent marker holders
For WM markers
Description
1SNC160251F0014–– Transparent marker holder profiled to allow marking on various cable sizes, up to ø 10 mm 0.394 in,–– Use with WM and WMTT markers,–– Made of PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-50°C to +80°C -58°F to +176°F

Ordering details
Wire ext. diameter
mm

in

Wire
sectionmm²

Holder length
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

For cable mounting
RING

RING

12 mm 0.472 in sealed transparent holder for WM12 and WMTT12 markers
1.5 ... 2.5 0.059 ... 0.098
12
0.472Transparent
RING122
2 ... 40.079 ... 0.157
Transparent
RING124
4 ... 70.157 ... 0.276
Transparent
RING127
6 ... 100.236 ... 0.394
Transparent
RING1210
18 mm 0.709 in sealed transparent holder for WM18 and WMTT18 markers
1.5 ... 2.5 0.059 ... 0.098
18
0.709
Transparent
RING182
2 ... 40.079 ... 0.157
Transparent
RING184
4 ... 70.157 ... 0.276
Transparent
RING187
6 ... 100.236 ... 0.394
Transparent
RING1810

1SNA235117R1000
1SNA235118R2100
1SNA235119R2200
1SNA235120R2700

3000
3000
2000
2000

1.80
2.20
0.30
0.50

1SNA235123R1600
1SNA235124R1700
1SNA235125R1000
1SNA235126R1100

3000
3000
2000
1000

0.30
0.30
0.50
0.70

1SNA235129R2400
1SNA235130R2100
1SNA235131R1600
1SNA235132R1700

1000
1000
500
500

0.40
0.40
0.50
1.40

1SNA235133R1000
1SNA235134R1100
1SNA235135R1200
1SNA235136R1300

500
500
200
200

0.40
0.60
0.90
2.20

1SNA235137R1400

200

0.40

4

SNAP

SNAP

12 mm 0.472 in un-sealed transparent holder for WM12 and WMTT12 markers
2 ... 3.5
0.079 ... 0.138
15
0.591
Transparent
SNAP152
2.8 ... 50.110 ... 0.197
Transparent
SNAP154
5 ... 80.197 ... 0.315
Transparent
SNAP157
8 ... 100.315 ... 0.394
Transparent
SNAP1510
23 mm 0.906 in in un-sealed transparent holder for WM18 and WMTT18 markers
2 ... 3.5
0.079 ... 0.138
23
0.906
Transparent
SNAP232
2.8 ... 50.110 ... 0.197
Transparent
SNAP234
5 ... 80.197 ... 0.315
Transparent
SNAP237
8 ... 100.315 ... 0.394
Transparent
SNAP2310

For thick tube mounting
RINGT23
23 mm 0.906 in tie-on sealed transparent holder for WM and WMTT markers
23
0.906
Transparent
RINGT23

1SNC160137S0201

RINGT23

Use holders only with designated cable marker of the same or a shorter length.

PAGE 99

PCGS wire and cable markers
Slide-in precut blank labels

1SNC700181F0000

Description

PCGS209–– Blank marker card for thick wires,–– To be inserted in RINGT209 holder,–– Made of PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +60°C -40°F to +140°F

Ordering details
Dimensionsmm

Nb. ofmarkers
per card

in

Color

Type

Part Number

Pkg

Weightcard(1 card) g

PCGS
For RINGT holders
20 x 9.3
0.787 x 0.366

60

White

PCGS209

1SNA235150R0500

40

10.00

SPRC 21

1SNA360031R0600

1

500.00Pkg

Weightpce(1 pce) g

240

6.00

Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

Use holders only with designated cable marker of the same or a shorter length.

4

RINGT209 transparent marker holders
For PCGS markers

1SNC160100F0014

Description

RINGT209–– Transparent tie-on marker holders profiled to allow thick tube identification,–– Use with PCGS209 markers,–– Made of PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-50°C to +80°C -58°F to +176°F

Ordering details
Dimensions
mm

Color

Type

Part Numberin

For thick tube mounting
RINGT209
Tie-on sealed transparent holder for PCGS markers
9.5 x 200.374 x 0.787
Transparent

RINGT209

1SNA235142R2100

1SNC160121S0201

Use holders only with designated cable marker of the same or a shorter length.
Dimensions given apply to the labelling area.

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRCCV wire and cable markers
Slide-in blank label

1SNC700227F0000

Description

RCCV–– Blank marker card for wire and cable identification,–– Markers are protected in the marker holders,–– To be slided in PETC transparent holder,–– Made of halogen-free PVC.

Main technical data
Material
PVC

Flammability
V0

Temperature range-20°C to +60°C -4°F to +140°F

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Card of 48 blank markers compatible with PETC holders
4.2 x 16.5 0.165 x 0.650
48
White

Part Number

Pkg

Weightpce(1 pce) g

RCCV

1SNA235460R0400

1

10.00

SPRCC 2

1SNA360011R0200

1

330.00Marking system accessories
SPRCC 2
Support plate for AMS600
Purchased separately

Mounting instruction
4

PETC transparent marker holders
For RCCV makers–– Transparent marker holder for wire and cable identification,–– To be used with RCCV markers,–– Made of PVC.

Main technical data
Material
PVC

Flammability

Temperature range-20°C to +90°C -4°F to +194°F

Ordering details
Wire ext. diameter

Wire
sectionin
mm²
0.043 ... 0.130 0.1 ... 1
0.059 ... 0.177 1 ... 2.5
0.118 ... 0.315 2.5 ... 10

Holder length

mm
1.1 ... 3.3
1.5 ... 4.5
3 ... 8

mm
18

in
0.709

Color

Type

Part Number

Transparent
Transparent
Transparent

PETC 51
PETC 53
PETC 56

1SNA168737R0200
1SNA168741R1600
1SNA168747R1400

Pkg

Weightpce(1 pce) g

100
100
100

PAGE 101

1SNC160134S0201

1SNC160251F0014

DescriptionRPA, PIB2 component and equipment markers
Self-adhesive precut blank labels

1SNC700241F0000

Description

PIB2–– Self-adhesive precut blank labels for general purpose,–– High performance adhesive compatible with most surface types.

Main technical data
Material
PVC

Flammability

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

RPA
8 x 17.5

0.315 x 0.689

16

White

RPA

1SNA235463R2300

50

0.20

PIB2
35 x 17.5

1.378 x 0.689

7

White

PIB2

1SNA235461R2100

50

0.60

SPRC 13

1SNA360023R0600

1

260.00Marking system accessories
SPRC 13
Support plate for AMS600 and AMS250
Purchased separately
4

1SNC160126S0201

Mounting instruction

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSPSP component and equipment markers
Self-adhesive precut blank labels

PSP–– Self-adhesive blank precut markers with round shaped edges,–– Can be used as plate for sub-assembly identification,–– Double-layered, can be engraved (black layer underneath).

Main technical data
Material
MMA

Flammability
UB

Temperature range-40°C to +82°C -40°F to +180°F

Ordering details
Dimensionsmm
15 x 50in
0.591 x 1.969

Nb. ofmarkers
per card
55

Color

White

Type

Part Number

PSP5015

1SNA235109R0100

SPRC 21

1SNA360031R0600

Pkg

Weightcard(1 card) g

2

10.00

1

500.00Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

4Compatible holders
PCT100015

1SNC160221S0201

1SNC700199F0000

Description

PAM100015

Protective cover and self-adhesive marking profile

PAGE 103

PAM component and equipment markers
Self-adhesive precut blank labels

1SNC700197F0000

Description

PAM–– Self-adhesive blank labels used to identified different components and equipments in a cabinet,–– Can be used directly on equipment.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +60°C -40°F to +140°F

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

20
20

12.00
22.00

20
20

14.00
27.00

1

300.00PAM
Self-adhesive blank label compatible with PAM100015 and PCT100015 transparent cover
15 x 215
0.591 x 8.465
2
White
PAM21515
1SNA235103R2300
15 x 430
0.591 x 16.930
White
PAM43015
1SNA235104R2400
Self-adhesive blank label
20 x 215
0.787 x 8.465
2
White
PAM21520
1SNA235105R2500
20 x 430
0.787 x 16.930
White
PAM43020
1SNA235106R2600

Marking system accessories
SPRC 27
Support plate for AMS600
Purchased separately

SPRC 27

1SNA360037R0400

Compatible holders
PCT100015

PAM100015

Protective cover and self-adhesive marking profile(only for PAM21515 and PAM43015)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160130S0201

4

BA4 component and equipment markers
Precut blank label–– Precut blank label used to identify contactors, overload relays and manual motor starters,–– Compatible with: AF09 ... AF370 contactors, TF thermal overload relays, EF electronic overload relays, andMS116, MS132 manual motor starters.

Main technical data
Material
Polycarbonate

Flammability
V0

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightcard(1 card) g

BA4
Card of 16 blank labels
7 x 200.276 x 0.787

White

BA4

1SNA235156R2700

16

11.00

SPRC 1

1SNA360010R1500

1

1500.00

Marking system accessories
SPRC 1
Support plate for AMS600
Included in KIT MAO AMS 600

4

Mounting instruction

1SNC160127S0201 - Rev. A

1SNC160101F0014

Description

PAGE 105PPB component and equipment markers
Two-colored precut blank labels

1SNC700200F0000

Description

PPB–– Two-colored blank label cards, white side / black side,–– For push button or sub-assembly identification,–– To be used with a label holder.

Main technical data
Material
MMA

Flammability
HB

Temperature range-40°C to +82°C -40°F to +180°F

Ordering details
Dimensionsmm
15 x 27in
0.591 x 1.063

Nb. ofmarkers
per card
16

Color

Type

Part Number

White and BlackPPB2715

1SNA235111R1200

SPRC 21

1SNA360031R0600

Pkg

Weightcard(1 card) g

12

13.30

1

500.00Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

4Compatible holders

PAM100015

Protective cover and self-adhesive marking profile

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

KA1-8120
Push button marker holder

1SNC160132S0201

PCT100015

PAM100015, PCT, KA marker holders
For component and equipment markers
Description

1SNC160268F0014–– Self-adhesive marking profile (PAM), transparent cover (PCT) and push-button marker holder (KA1),–– To be used with PAM21515, PAM43015, PSP and PPB labels.

Main technical data
Material
PVC (for PAM and PCT)
Polycarbonate (for KA1)

Flammability
V0 (for PAM and PCT)
V2 (for KA1)

Temperature range-10°C to +70°C +14°F to +158°F (for PAM and PCT)
-25°C to +70°C -13°F to +158°F (for KA1)

Ordering details
Dimensions
mm

Color

Type

Part Number

in

Pkg

Weightpce(1 pce) g

10

2.00

Push-button marker holder
KA1
Push button marker holder for PPB markers.
15 x 270.591 x 1.063
KA1-8120

Black

KA1-8120

1SFA616920R8120

Self-adhesive marking profile for PAM, PSP and PPB markers.
PCT

PCT100015

Transparent cover for PAM100015
15 x 1000
0.591 x 39.370

Transparent

PCT100015

1SNA235147R2600

35

34.00

Self-adhesive marking profile for PAM, PSP and PPB markers.
15 x 1000
0.591 x 39.370
Black
PAM100015

1SNA235146R2500

35

40.00

PAM100015

Dimensions given apply to the labelling area.

1SNC160131S0201

PAM100015

4

PAGE 107

PAT panel plates
Self-adhesive blank panel plates

1SNC700214F0000

Description

PAT–– Self-adhesive blank plate for identification of electrical boxes or cabinets.

Main technical data
Material
PVC

Flammability
V0

Temperature range-40°C to +120°C -40°F to +248°F

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightpce(1 pce) g

PATAdhesive plate for external marking
60 x 100
2.262 x 3.937
1

White

PAT10060

1SNA235114R1500

15

5.30

SPRC 21

1SNA360031R0600

1

500.00Pkg

Weightpce(1 pce) g

Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

PPT panel plates
Blank panel plates
Description
1SNC700213F0000

PPT–– Blank perforated plate for identification of electrical boxes or cabinets,–– To be fixed with rivets.

Main technical data
Material
MMA

Flammability
HB

Temperature range-40°C to +82°C -40°F to +180°F

Ordering details
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

PPT
Perforated blank plate
30 x 1201.181 x 4.724
50 x 180
1.969 x 7.087

1

White
White

PPT12030
PPT18050

1SNA235115R1600
1SNA235116R1700

50
30

3.50
8.80

SPRC 21

1SNA360031R0600

1

500.00Marking system accessories
SPRC 21
Support plate for AMS600 and AMS250
Purchased separately

Mounting instruction
23 mm
0.91"
113 mm4.45"

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160136S0201

4

PB111

4

PAGE 109

Summary_5

5INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSSolution series
Pre-printed markers

SNK series terminal block identification
5.2 mm 0.205 in spacing

horizontal mounting112

		
vertical mounting
6 mm 0.236 in spacing
MC612PAhorizontal mounting

114
116

		
vertical mounting
8 mm 0.315 in spacing
MC812PAhorizontal mounting

118
120

		
vertical mounting

122

SNA series terminal block identification
4 mm 0.157 in spacing

horizontal mounting

124

		vertical mounting
RC510
horizontal mounting
5 mm 0.197 in spacing

126
128

		
vertical mounting
RC610
horizontal mounting
6 mm 0.236 in spacing

130
132

		
vertical mounting
RC810
horizontal mounting
8 mm 0.315 in spacing

135
137

		
vertical mounting
RC1010horizontal mounting
10 mm 0.394 in spacing

139
140

		
vertical mounting

141

Specific terminal block identification
5 mm 0.197 in spacing

MC512PA

RC410

horizontal mounting142		vertical mounting
6 mm 0.236 in spacing
RC65
horizontal mounting

144
145

		
vertical mounting
8 mm 0.315 in spacing
RCAL85horizontal mounting

147
149

		
vertical mounting
6 mm 0.236 in spacing
RCT		
RTM
top marking
6 mm 0.236 in to 12 mm 0.472 in spacing
13 mm 0.512 in or 16 mm 0.630 in spacing
REH3		EPU
top marking
5 mm 0.197 in to 12 mm 0.472 in spacing
6 mm 0.236 in to 22 mm 0.866 in spacingEP
top marking

150
151
152
153
154
155

RC55

5

Customized marking
156

Summary_5

Order form

PAGE 111

MC512PA terminal block markers
Pre-printed markers for SNK series - 5.2 mm 0.205 in spacing - horizontal mounting
Description–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols.

1SNC160191F0014

Main technical data

Horizontal terminal blockassembly

5
1

2

3

4

5

6

7

8

9 10

11 12 13 14 15 16 17 18 19 20

21 22 23 24 25 26 27 28 29 30

31 32 33 34 35 36 37 38 39 40

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100)
White
7 (x100)
White
8 (x100)
White
9 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK140091R0000
1SNK140011R0000
1SNK140021R0000
1SNK140031R0000
1SNK140041R0000
1SNK140051R0000
1SNK140061R0000
1SNK140071R0000
1SNK140081R0000
1SNK140083R0000
1SNK140101R0000
1SNK140111R0000
1SNK140121R0000
1SNK140131R0000
1SNK140141R0000
1SNK140151R0000
1SNK140161R0000
1SNK140171R0000
1SNK140181R0000
1SNK140191R0000
1SNK140201R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK145011R0000
1SNK145021R0000
1SNK145031R0000
1SNK145041R0000
1SNK145051R0000
1SNK145061R0000
1SNK145071R0000
1SNK145081R0000
1SNK145091R0000

5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK147001R0000
1SNK147011R0000
1SNK147021R0000
1SNK147031R0000
1SNK147041R0000
1SNK147051R0000
1SNK147061R0000
1SNK147071R0000
1SNK147081R0000
1SNK147091R0000

5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

1SNC160159S0201

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSMC512PA terminal block markers
Pre-printed markers for SNK series - 5.2 mm 0.205 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)
Card with 100 markers, repeated identical symbols+ (x100)- (x100)~ (x100)= (x100)(x100)
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK146011R0000
1SNK146021R0000
1SNK146031R0000
1SNK146041R0000
1SNK146051R0000
1SNK146061R0000
1SNK146071R0000
1SNK146081R0000
1SNK146091R0000
1SNK146101R0000
1SNK146111R0000
1SNK146121R0000
1SNK146131R0000
1SNK146141R0000
1SNK146151R0000
1SNK146161R0000
1SNK146171R0000
1SNK146181R0000
1SNK146191R0000
1SNK146201R0000
1SNK146211R0000
1SNK146221R0000
1SNK146231R0000
1SNK146241R0000
1SNK146251R0000
1SNK146261R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK148001R0000
1SNK148011R0000
1SNK148021R0000
1SNK148031R0000
1SNK148041R0000
1SNK148051R0000
1SNK148061R0000
1SNK148071R0000
1SNK148091R0000
1SNK148101R0000
1SNK148111R0000
1SNK148121R0000
1SNK148131R0000
1SNK148141R0000
1SNK148151R0000
1SNK148161R0000
1SNK148171R0000
1SNK148181R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)White

MC512PA1SNK149001R0000

5

10.00

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)White

MC512PA1SNK149011R0000

5

10.00

5

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

U1 U2 U3 V1 V2 V3 W1 W2 W3 U1

1SNC160159S0201

U1 U2 U3 V1 V2 V3 W1 W2 W3 U1U1 U2 U3 V1 V2 V3 W1 W2 W3 U1U1 U2 U3 V1 V2 V3 W1 W2 W3 U1PAGE 113

MC512PA terminal block markers
Pre-printed markers for SNK series

5.2 mm 0.205 in spacing - vertical mounting
Description
1SNC160190F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols.

Vertical terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Description

9

10
30
3
0
A
A

A

A

0

0

0

40

20

8

29
2
0
A
A

A

A

0

0

0

39
39

19

7

28
2
0
A
A

A

A

0

0

0

38
38

18

6

27
2
0
A
A

A

A

0

0

0

37

17

5

26
2
0
A
A

A

A

0

0

0

36
36

16

4

25
2
0
A
A

A

A

0

0

0

35
35

15

3

0
A
A

A

A

0

0

0

24
2

14

2

34
34

13
23
2
33
33
0
A
A

A

A

0

0

0

22
2

11
21
2

32
32
0
0

0

0

0
A
A
A

A

A
A

A

A

0

0

0

31

12

1

5

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100)
White
7 (x100)
White
8 (x100)
White
9 (x100)
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK140092R0000
1SNK140012R0000
1SNK140022R0000
1SNK140032R0000
1SNK140042R0000
1SNK140052R0000
1SNK140062R0000
1SNK140072R0000
1SNK140082R0000
1SNK140084R0000
1SNK140102R0000
1SNK140112R0000
1SNK140122R0000
1SNK140132R0000
1SNK140142R0000
1SNK140152R0000
1SNK140162R0000
1SNK140172R0000
1SNK140182R0000
1SNK140192R0000
1SNK140202R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK145012R0000
1SNK145022R0000
1SNK145032R0000
1SNK145042R0000
1SNK145052R0000
1SNK145062R0000
1SNK145072R0000
1SNK145082R0000
1SNK145092R0000
1SNK145102R0000

5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK147002R0000
1SNK147012R0000
1SNK147022R0000
1SNK147032R0000
1SNK147042R0000
1SNK147052R0000
1SNK147062R0000
1SNK147072R0000
1SNK147082R0000
1SNK147092R0000

5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK146012R0000
1SNK146022R0000
1SNK146032R0000
1SNK146042R0000
1SNK146052R0000
1SNK146062R0000
1SNK146072R0000
1SNK146082R0000
1SNK146092R0000
1SNK146102R0000

5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160160S0201

Ordering details

MC512PA terminal block markers
Pre-printed markers for SNK series

5.2 mm 0.205 in spacing - vertical mounting
Ordering details

+

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK146112R0000
1SNK146122R0000
1SNK146132R0000
1SNK146142R0000
1SNK146152R0000
1SNK146162R0000
1SNK146172R0000
1SNK146182R0000
1SNK146192R0000
1SNK146202R0000
1SNK146212R0000
1SNK146222R0000
1SNK146232R0000
1SNK146242R0000
1SNK146252R0000
1SNK146262R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

Card with 100 markers, repeated identical symbols+ (x100)- (x100)~ (x100)= (x100)(x100)
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)+24V (x100)+48V (x100)-24V (x100)-48V (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK148002R0000
1SNK148012R0000
1SNK148022R0000
1SNK148032R0000
1SNK148042R0000
1SNK148052R0000
1SNK148062R0000
1SNK148072R0000
1SNK148092R0000
1SNK148102R0000
1SNK148112R0000
1SNK148122R0000
1SNK148132R0000
1SNK148142R0000
1SNK148152R0000
1SNK148162R0000
1SNK148172R0000
1SNK148182R0000
1SNK148192R0000
1SNK148202R0000
1SNK148212R0000
1SNK148222R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00
10.00

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)White

MC512PA1SNK149002R0000

5

10.00

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)White

MC512PA1SNK149012R0000

5

10.00

5

U1
U
U1

U1

1SNC160160S0201

+

+
+
PE
P

Color

U1

PE

PE

PE

+

+

+
+
N
W3
W
W3
W3

W3

W3

N

N

N

+

+

+
+
L3
L
W2
W
W2
W2

W2

W2

L3
L3

L3

L3

+

+

+
+
L2
L
W1
W
W1
W1

W1

W1

L2
L2

L2

L2

+

+

+
+
L1
L
V3
V
V3

V3

V3

L1

L1

L1

+

+

+
+
PE
P
V2
V
V2

V2

V2

PE

PE

PE

+

+

+
+
N
V1
V
V1

V1

V1

N

N

N

+

+

+
+
L3
L
U3
U
U3

U3

U3

L3
L3

L3

+

+

L3

+

+

+

+

L2
L2
L

L2

L1
L

L2
L2
U2
U2
U
U2

U2

U1
U
U1

U1

U1

L1

L1

L1

+

+

Description

PAGE 115

MC612PA terminal block markers
Pre-printed markers for SNK series

6 mm 0.236 in spacing - horizontal mounting
Description–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols.

Horizontal terminal blockassembly

5

1

2

3

4

5

6

7

8

9 10

11 12 13 14 15 16 17 18 19 20

21 22 23 24 25 26 27 28 29 30

31 32 33 34 35 36 37 38 39 40

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100)
White
7 (x100)
White
8 (x100)
White
9 (x100)
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White
K (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK150091R0000
1SNK150011R0000
1SNK150021R0000
1SNK150031R0000
1SNK150041R0000
1SNK150051R0000
1SNK150061R0000
1SNK150071R0000
1SNK150081R0000
1SNK150083R0000
1SNK150101R0000
1SNK150111R0000
1SNK150121R0000
1SNK150131R0000
1SNK150141R0000
1SNK150151R0000
1SNK150161R0000
1SNK150171R0000
1SNK150181R0000
1SNK150191R0000
1SNK150201R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK155011R0000
1SNK155021R0000
1SNK155031R0000
1SNK155041R0000
1SNK155051R0000
1SNK155061R0000
1SNK155071R0000
1SNK155081R0000
1SNK155091R0000

5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK157001R0000
1SNK157011R0000
1SNK157021R0000
1SNK157031R0000
1SNK157041R0000
1SNK157051R0000
1SNK157061R0000
1SNK157071R0000
1SNK157081R0000
1SNK157091R0000

5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK156011R0000
1SNK156021R0000
1SNK156031R0000
1SNK156041R0000
1SNK156051R0000
1SNK156061R0000
1SNK156071R0000
1SNK156081R0000
1SNK156091R0000
1SNK156101R0000
1SNK156111R0000

5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160161S0201

1SNC160191F0014

Main technical dataMC612PA terminal block markers
Pre-printed markers for SNK series

6 mm 0.236 in spacing - horizontal mounting
Ordering details
Description

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous pageL (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK156121R0000
1SNK156131R0000
1SNK156141R0000
1SNK156151R0000
1SNK156161R0000
1SNK156171R0000
1SNK156181R0000
1SNK156191R0000
1SNK156201R0000
1SNK156211R0000
1SNK156221R0000
1SNK156231R0000
1SNK156241R0000
1SNK156251R0000
1SNK156261R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

Card with 100 markers, repeated identical symbols+ (x100)- (x100)~ (x100)= (x100)(x100)
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK158001R0000
1SNK158011R0000
1SNK158021R0000
1SNK158031R0000
1SNK158041R0000
1SNK158051R0000
1SNK158061R0000
1SNK158071R0000
1SNK158091R0000
1SNK158101R0000
1SNK158111R0000
1SNK158121R0000
1SNK158131R0000
1SNK158141R0000
1SNK158151R0000
1SNK158161R0000
1SNK158171R0000
1SNK158181R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)White

MC612PA1SNK159001R0000

5

11.00

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)White

MC612PA1SNK159011R0000

5

11.00

5

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

U1 U2 U3 V1 V2 V3 W1 W2 W3 U1U1 U2 U3 V1 V2 V3 W1 W2 W3 U1U1 U2 U3 V1 V2 V3 W1 W2 W3 U1

1SNC160161S0201

U1 U2 U3 V1 V2 V3 W1 W2 W3 U1PAGE 117

MC612PA terminal block markers
Pre-printed markers for SNK series

6 mm 0.236 in spacing - vertical mounting
Description
1SNC160190F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols.

Vertical terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Description

9

10
30
3
0
A
A

A

A

0

0

0

40

20

8

29
2
0
A
A

A

A

0

0

0

39
39

19

7

28
2
0
A
A

A

A

0

0

0

38
38

18

6

27
2
0
A
A

A

A

0

0

0

37

17

5

26
2
0
A
A

A

A

0

0

0

36
36

16

4

25
2
0
A
A

A

A

0

0

0

35
35

15

3

0
A
A

A

A

0

0

0

24
2

14

2

34
34

13
23
2
33
33
0
A
A

A

A

0

0

0

22
2

11
21
2

32
32
0
0

0

0

0
A
A
A

A

A
A

A

A

0

0

0

31

12

1

5

Color

Card with 100 markers, ascending order repeated 10 times
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
0->9 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100)
White
7 (x100)
White
8 (x100)
White
9 (x100)
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK150012R0000
1SNK150022R0000
1SNK150032R0000
1SNK150042R0000
1SNK150052R0000
1SNK150062R0000
1SNK150072R0000
1SNK150082R0000
1SNK150084R0000
1SNK150092R0000
1SNK150102R0000
1SNK150112R0000
1SNK150122R0000
1SNK150132R0000
1SNK150142R0000
1SNK150152R0000
1SNK150162R0000
1SNK150172R0000
1SNK150182R0000
1SNK150192R0000
1SNK150202R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK155012R0000
1SNK155022R0000
1SNK155032R0000
1SNK155042R0000
1SNK155052R0000
1SNK155062R0000
1SNK155072R0000
1SNK155082R0000
1SNK155092R0000
1SNK155102R0000

5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK157002R0000
1SNK157012R0000
1SNK157022R0000
1SNK157032R0000
1SNK157042R0000
1SNK157052R0000
1SNK157062R0000
1SNK157072R0000
1SNK157082R0000
1SNK157092R0000

5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK156012R0000
1SNK156022R0000
1SNK156032R0000
1SNK156042R0000
1SNK156052R0000
1SNK156062R0000
1SNK156072R0000
1SNK156082R0000
1SNK156092R0000
1SNK156102R0000

5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160162S0201

Ordering details

MC612PA terminal block markers
Pre-printed markers for SNK series

6 mm 0.236 in spacing - vertical mounting
Ordering details

+

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK156112R0000
1SNK156122R0000
1SNK156132R0000
1SNK156142R0000
1SNK156152R0000
1SNK156162R0000
1SNK156172R0000
1SNK156182R0000
1SNK156192R0000
1SNK156202R0000
1SNK156212R0000
1SNK156222R0000
1SNK156232R0000
1SNK156242R0000
1SNK156252R0000
1SNK156262R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

Card with 100 markers, repeated identical symbols+ (x100)- (x100)~ (x100)= (x100)(x100)
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)+24V (x100)+48V (x100)- 24V (x100)-48V (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK158002R0000
1SNK158012R0000
1SNK158022R0000
1SNK158032R0000
1SNK158042R0000
1SNK158052R0000
1SNK158062R0000
1SNK158072R0000
1SNK158092R0000
1SNK158102R0000
1SNK158112R0000
1SNK158122R0000
1SNK158132R0000
1SNK158142R0000
1SNK158152R0000
1SNK158162R0000
1SNK158172R0000
1SNK158182R0000
1SNK158192R0000
1SNK158202R0000
1SNK158212R0000
1SNK158222R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00
11.00

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)White

MC612PA1SNK159002R0000

5

11.00

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)White

MC612PA1SNK159012R0000

5

11.00

U1
U
U1

5

1SNC160162S0201

+

+
PE
PE
P

Color

U1

U1

PE

PE

+

+

+

+
N
N
W3
W
W3
W3

W3

W3

N

N

+

+

+

+
L3
L3
L
W2
W
W2
W2

W2

W2

L3
L3

L3

+

+

+

+
L2
L2
L
W1
W
W1
W1

W1

W1

L2
L2

L2

+

+

+

+
L1
L1
L
V3
V
V3

V3

V3

L1

L1

+

+

+

+
PE
PE
P
V2
V
V2

V2

V2

PE

PE

+

+

+

+
+
N
N
N
V1
V
V1

V1

V1

N

L3
L3
L
U3
U
U3

U3

U3

L3
L3

L3

+

+
+

+
+

+

+

+
L2

+

L1

L2
L

L2

L1
L

L2
L2
U2
U2
U
U2

U2

U1
U
U1

U1

U1

L1

L1

+

+

+

Description

PAGE 119

MC812PA terminal block markers
Pre-printed markers for SNK series

8 mm 0.315 in spacing - horizontal mounting
Description–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols.

Horizontal terminal blockassembly

5

1

2

3

4

5

6

7

8

9 10

11 12 13 14 15 16 17 18 19 20

21 22 23 24 25 26 27 28 29 30

31 32 33 34 35 36 37 38 39 40

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

A

Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100)
White
7 (x100)
White
8 (x100)
White
9 (x100)
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White
K (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK160091R0000
1SNK160011R0000
1SNK160021R0000
1SNK160031R0000
1SNK160041R0000
1SNK160051R0000
1SNK160061R0000
1SNK160071R0000
1SNK160081R0000
1SNK160083R0000
1SNK160101R0000
1SNK160111R0000
1SNK160121R0000
1SNK160131R0000
1SNK160141R0000
1SNK160151R0000
1SNK160161R0000
1SNK160171R0000
1SNK160181R0000
1SNK160191R0000
1SNK160201R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK165011R0000
1SNK165021R0000
1SNK165031R0000
1SNK165041R0000
1SNK165051R0000
1SNK165061R0000
1SNK165071R0000
1SNK165081R0000
1SNK165091R0000

5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK167001R0000
1SNK167011R0000
1SNK167021R0000
1SNK167031R0000
1SNK167041R0000
1SNK167051R0000
1SNK167061R0000
1SNK167071R0000
1SNK167081R0000
1SNK167091R0000

5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166011R0000
1SNK166021R0000
1SNK166031R0000
1SNK166041R0000
1SNK166051R0000
1SNK166061R0000
1SNK166071R0000
1SNK166081R0000
1SNK166091R0000
1SNK166101R0000
1SNK166111R0000

5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160163S0201

1SNC160191F0014

Main technical data

MC812PA terminal block markers
Pre-printed markers for SNK series

8 mm 0.315 in spacing - horizontal mounting
Ordering details
Description

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

+

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous pageL (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166121R0000
1SNK166131R0000
1SNK166141R0000
1SNK166151R0000
1SNK166161R0000
1SNK166171R0000
1SNK166181R0000
1SNK166191R0000
1SNK166201R0000
1SNK166211R0000
1SNK166221R0000
1SNK166231R0000
1SNK166241R0000
1SNK166251R0000
1SNK166261R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

Card with 100 markers, repeated identical symbols+ (x100)- (x100)~ (x100)= (x100)(x100)
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK168001R0000
1SNK168011R0000
1SNK168021R0000
1SNK168031R0000
1SNK168041R0000
1SNK168051R0000
1SNK168061R0000
1SNK168071R0000
1SNK168091R0000
1SNK168101R0000
1SNK168111R0000
1SNK168121R0000
1SNK168131R0000
1SNK168141R0000
1SNK168151R0000
1SNK168161R0000
1SNK168171R0000
1SNK168181R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)White

MC812PA1SNK169001R0000

5

14.00

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)WhiteMC812PA1SNK169011R0000

5

14.00

5

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

L1 L2 L3 N PE L1 L2 L3 N PE

U1 U2 U3 V1 V2 V3 W1 W2 W3 U1U1 U2 U3 V1 V2 V3 W1 W2 W3 U1U1 U2 U3 V1 V2 V3 W1 W2 W3 U1

1SNC160163S0201

U1 U2 U3 V1 V2 V3 W1 W2 W3 U1PAGE 121

MC812PA terminal block markers
Pre-printed markers for SNK series

8 mm 0.315 in spacing - vertical mounting
Description
1SNC160190F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols.

Vertical terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Description

9

10
30
3
0
A
A

A

A

0

0

0

40

20

8

29
2
0
A
A

A

A

0

0

0

39
39

19

7

28
2
0
A
A

A

A

0

0

0

38
38

18

6

27
2
0
A
A

A

A

0

0

0

37

17

5

26
2
0
A
A

A

A

0

0

0

36
36

16

4

25
2
0
A
A

A

A

0

0

0

35
35

15

3

0
A
A

A

A

0

0

0

24
2

14

2

34
34

13
23
2
33
33
0
A
A

A

A

0

0

0

22
2

11
21
2

32
32
0
0

0

0

0
A
A
A

A

A
A

A

A

0

0

0

31

12

1

5

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100)
White
7 (x100)
White
8 (x100)
White
9 (x100)
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK160092R0000
1SNK160012R0000
1SNK160022R0000
1SNK160032R0000
1SNK160042R0000
1SNK160052R0000
1SNK160062R0000
1SNK160072R0000
1SNK160082R0000
1SNK160084R0000
1SNK160102R0000
1SNK160112R0000
1SNK160122R0000
1SNK160132R0000
1SNK160142R0000
1SNK160152R0000
1SNK160162R0000
1SNK160172R0000
1SNK160182R0000
1SNK160192R0000
1SNK160202R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK165012R0000
1SNK165022R0000
1SNK165032R0000
1SNK165042R0000
1SNK165052R0000
1SNK165062R0000
1SNK165072R0000
1SNK165082R0000
1SNK165092R0000
1SNK165102R0000

5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK167002R0000
1SNK167012R0000
1SNK167022R0000
1SNK167032R0000
1SNK167042R0000
1SNK167052R0000
1SNK167062R0000
1SNK167072R0000
1SNK167082R0000
1SNK167092R0000

5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166012R0000
1SNK166022R0000
1SNK166032R0000
1SNK166042R0000
1SNK166052R0000
1SNK166062R0000
1SNK166072R0000
1SNK166082R0000
1SNK166092R0000
1SNK166102R0000

5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160164S0201

Ordering details

MC812PA terminal block markers
Pre-printed markers for SNK series

8 mm 0.315 in spacing - vertical mounting
Ordering details

+

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166112R0000
1SNK166122R0000
1SNK166132R0000
1SNK166142R0000
1SNK166152R0000
1SNK166162R0000
1SNK166172R0000
1SNK166182R0000
1SNK166192R0000
1SNK166202R0000
1SNK166212R0000
1SNK166222R0000
1SNK166232R0000
1SNK166242R0000
1SNK166252R0000
1SNK166262R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

Card with 100 markers, repeated identical symbols+ (x100)- (x100)~ (x100)= (x100)(x100)
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)U1 (x100)
U2 (x100)
U3 (x100)V1 (x100)
V2 (x100)
V3 (x100)W1 (x100)W2 (x100)W3 (x100)+24V (x100)+48V (x100)-24V (x100)-48V (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK168002R0000
1SNK168012R0000
1SNK168022R0000
1SNK168032R0000
1SNK168042R0000
1SNK168052R0000
1SNK168062R0000
1SNK168072R0000
1SNK168092R0000
1SNK168102R0000
1SNK168112R0000
1SNK168122R0000
1SNK168132R0000
1SNK168142R0000
1SNK168152R0000
1SNK168162R0000
1SNK168172R0000
1SNK168182R0000
1SNK168192R0000
1SNK168202R0000
1SNK168212R0000
1SNK168222R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00
14.00

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)White

MC812PA1SNK169002R0000

5

14.00

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)WhiteMC812PA1SNK169012R0000

5

14.00

U1
U
U1

5

1SNC160164S0201

+

+
+
PE
P

Color

U1

U1

PE

PE

PE

+

+

+
+
N
W3
W
W3
W3

W3

W3

N

N

N

+

+

+
+
L3
L
W2
W
W2
W2

W2

W2

L3
L3

L3

L3

+

+

+
+
L2
L
W1
W
W1
W1

W1

W1

L2
L2

L2

L2

+

+

+
+
L1
L
V3
V
V3

V3

V3

L1

L1

L1

+

+

+
+
PE
P
V2
V
V2

V2

V2

PE

PE

PE

+

+

+
+
N
V1
V
V1

V1

V1

N

N

N

+

+

+
+
L3
L
U3
U
U3

U3

U3

L3
L3

L3

+

+

L3

+

+

+

+

L2
L2
L

L2

L1
L

L2
L2
U2
U2
U
U2

U2

U1
U
U1

U1

U1

L1

L1

L1

+

+

Description

PAGE 123

RC410 terminal block markers
Pre-printed markers for SNA and Solution series

4 mm 0.157 in spacing - horizontal mounting
Description

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark spring clamp terminal blocks and screw clamp miniblocks (DR..) from the SNA and
Solution series.

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
Card with 100 markers, ascending order
1->100White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100) / 9 (x100)
White
7 (x100)
White
8 (x100)White
10 (x100)White
11 (x100)White
12 (x100)White
13 (x100)White
14 (x100)White
15 (x100)White
16 (x100)White
17 (x100)White
18 (x100)White
19 (x100)White
20 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA229001R0200
1SNA229002R0300
1SNA229003R0400
1SNA229004R0500
1SNA229005R0600
1SNA229006R0700
1SNA229007R0000
1SNA229008R1100
1SNA229009R1200
1SNA229010R0600
1SNA229011R2300

5
5
5
5
5
5
5
5
5
5
5

5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20

RC410

1SNA229030R0200

5

5.20

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA229210R1300
1SNA229211R0000
1SNA229212R0100
1SNA229213R0200
1SNA229214R0300
1SNA229215R0400
1SNA229216R0500
1SNA229217R0600
1SNA229218R1700
1SNA229220R1500
1SNA229221R0200
1SNA229222R0300
1SNA229223R0400
1SNA229224R0500
1SNA229225R0600
1SNA229226R0700
1SNA229227R0000
1SNA229228R1100
1SNA229229R1200
1SNA229230R1700

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20

Continue on next page →1SNC160138S0201

5

Color

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC410 terminal block markers
Pre-printed markers for SNA and Solution series

4 mm 0.157 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA229150R1700
1SNA229151R0400
1SNA229152R0500
1SNA229153R0600
1SNA229154R0700
1SNA229155R0000
1SNA229156R0100
1SNA229157R0200
1SNA229158R1300
1SNA229159R1400
1SNA229160R1100
1SNA229161R0600
1SNA229162R0700
1SNA229163R0000
1SNA229164R0100
1SNA229165R0200
1SNA229166R0300
1SNA229167R0400
1SNA229168R1500
1SNA229169R1600
1SNA229170R1300
1SNA229171R0000
1SNA229172R0100
1SNA229173R0200
1SNA229174R0300
1SNA229175R0400

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20

White
White
White
White
White

RC410
RC410
RC410
RC410
RC410

1SNA229111R2400
1SNA229112R2500
1SNA229113R2600
1SNA229114R2700
1SNA229115R2000

5
5
5
5
5

5.20
5.20
5.20
5.20
5.20

5

1SNC160138S0201

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)
Card with 100 markers, repeated identical symbols+ (x100)- (x100)= (x100)~ (x100)(x100)

PAGE 125

RC410 terminal block markers
Pre-printed markers for SNA and Solution series

4 mm 0.157 in spacing - vertical mounting

1SNC160190F0014

Description

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark spring clamp terminal blocks and screw clamp miniblocks (DR..) from the SNA and
Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA229040R1400
1SNA229041R0100
1SNA229042R0200
1SNA229043R0300
1SNA229044R0400
1SNA229045R0500
1SNA229046R0600
1SNA229047R0700
1SNA229048R1000
1SNA229049R1100
1SNA229050R1600
1SNA229051R0300
1SNA229052R0400
1SNA229053R0500
1SNA229054R0600
1SNA229055R0700
1SNA229056R0000
1SNA229057R0100
1SNA229058R1200
1SNA229059R1300
1SNA229072R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA229060R1000
1SNA229061R0500
1SNA229062R0600
1SNA229063R0700
1SNA229064R0000
1SNA229065R0100
1SNA229066R0200
1SNA229067R0300
1SNA229068R1400
1SNA229069R1500

5
5
5
5
5
5
5
5
5
5

5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20

Continue on next page →1SNC160139S0201

5

Color

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC410 terminal block markers
Pre-printed markers for SNA and Solution series

4 mm 0.157 in spacing - vertical mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA229180R0600
1SNA229181R2300
1SNA229182R2400
1SNA229183R2500
1SNA229184R2600
1SNA229185R2700
1SNA229186R2000
1SNA229187R2100
1SNA229188R0200
1SNA229189R0300
1SNA229190R0000
1SNA229191R2500
1SNA229192R2600
1SNA229193R2700
1SNA229194R2000
1SNA229195R2100
1SNA229196R2200
1SNA229197R2300
1SNA229198R0400
1SNA229199R0500
1SNA229200R2200
1SNA229201R1700
1SNA229202R1000
1SNA229203R1100
1SNA229204R1200
1SNA229205R1300

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20
5.20

5

1SNC160139S0201

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

PAGE 127

RC510 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - horizontal mounting
Description

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

5

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100) / 9 (x100)
White
7 (x100)
White
8 (x100)White
10 (x100)White
11 (x100)White
12 (x100)White
13 (x100)White
14 (x100)White
15 (x100)White
16 (x100)White
17 (x100)White
18 (x100)White
19 (x100)White
20 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA231001R2400
1SNA231002R2500
1SNA231003R2600
1SNA231004R2700
1SNA231005R2000
1SNA231006R2100
1SNA231007R2200
1SNA231008R0300
1SNA231009R0400
1SNA231010R2000
1SNA231011R1500
1SNA231012R1600
1SNA231013R1700
1SNA231014R1000
1SNA231015R1100
1SNA231016R1200
1SNA231017R1300
1SNA231018R2400
1SNA231019R2500
1SNA231020R2200
1SNA231021R1700

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA231030R2400
1SNA231031R1100
1SNA231032R1200
1SNA231033R1300
1SNA231034R1400
1SNA231035R1500
1SNA231036R1600
1SNA231037R1700
1SNA231038R2000
1SNA231039R2100

5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA231210R0500
1SNA231211R2200
1SNA231212R2300
1SNA231213R2400
1SNA231214R2500
1SNA231215R2600
1SNA231216R2700
1SNA231217R2000
1SNA231218R0100
1SNA231220R0700
1SNA231221R2400
1SNA231222R2500
1SNA231223R2600
1SNA231224R2700
1SNA231225R2000
1SNA231226R2100
1SNA231227R2200
1SNA231228R0300
1SNA231229R0400
1SNA231230R0100

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160140S0201

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring clamp, ADO System® and screw clamp pluggable (side marking)terminal blocks from the SNA and Solution series.

RC510 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA231150R0100
1SNA231151R2600
1SNA231152R2700
1SNA231153R2000
1SNA231154R2100
1SNA231155R2200
1SNA231156R2300
1SNA231157R2400
1SNA231158R0500
1SNA231159R0600
1SNA231160R0300
1SNA231161R2000
1SNA231162R2100
1SNA231163R2200
1SNA231164R2300
1SNA231165R2400
1SNA231166R2500
1SNA231167R2600
1SNA231168R0700
1SNA231169R0000
1SNA231170R0500
1SNA231171R2200
1SNA231172R2300
1SNA231173R2400
1SNA231174R2500
1SNA231175R2600

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

Card with 100 markers, repeated identical symbols+ (x100)- (x100)= (x100)~ (x100)(x100)

White
White
White
White
White

RC510
RC510
RC510
RC510
RC510

1SNA231111R1600
1SNA231112R1700
1SNA231113R1000
1SNA231114R1100
1SNA231115R1200

5
5
5
5
5

5.50
5.50
5.50
5.50
5.50

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)
White

RC510

1SNA231131R1200

5

5.50

Card with 100 markers, repeated identical symbols
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)

RC510
RC510
RC510
RC510

1SNA231116R1300
1SNA231117R1400
1SNA231118R2500
1SNA231119R2600

5
5
5
5

5.50
5.50
5.50
5.50

White
White
White
White

5

1SNC160140S0201

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

PAGE 129

RC510 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - vertical mounting

1SNC160190F0014

Description

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring clamp, ADO System® and screw clamp pluggable (side marking)terminal blocks from the SNA and Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

TypePart Number

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)RC510
1SNA231040R0600
White
1->10 (x10)RC510
1SNA231041R2300
White
11->20 (x10)RC510
1SNA231042R2400
White
21->30 (x10)RC510
1SNA231043R2500
White
31->40 (x10)RC510
1SNA231044R2600
White
41->50 (x10)RC510
1SNA231045R2700
White
51->60 (x10)RC510
1SNA231046R2000
White
61->70 (x10)RC510
1SNA231047R2100
White
71->80 (x10)RC510
1SNA231048R0200
White
81->90 (x10)RC510
1SNA231049R0300
White
91->100 (x10)RC510
1SNA231050R0000
White
101->110 (x10)RC510
1SNA231051R2500
White
111->120 (x10)RC510
1SNA231052R2600
White
121->130 (x10)RC510
1SNA231053R2700
White
131->140 (x10)RC510
1SNA231054R2000
White
141->150 (x10)RC510
1SNA231055R2100
White
151->160 (x10)RC510
1SNA231056R2200
White
161->170 (x10)RC510
1SNA231057R2300
White
171->180 (x10)RC510
1SNA231058R0400
White
181->190 (x10)RC510
1SNA231059R0500
White
191->200 (x10)RC510
1SNA231072R2200
White
Card with 100 markers, ascending order
1->100RC510
1SNA231060R0200
White
101->200
RC510
1SNA231061R2700
White
201->300
RC510
1SNA231062R2000
White
301->400
RC510
1SNA231063R2100
White
401->500
RC510
1SNA231064R2200
White
501->600
RC510
1SNA231065R2300
White
601->700
RC510
1SNA231066R2400
White
701->800
RC510
1SNA231067R2500
White
801->900
RC510
1SNA231068R0600
White
901->1000
RC510
1SNA231069R0700
White
Card with 100 markers, alternate odd/even numbers for double deck terminal blocks
1->20 alternate odd/even
RC510
1SNA231133R1400
White
21->40 alternate odd/even
RC510
1SNA231134R1500
White
41->60 alternate odd/even
RC510
1SNA231135R1600
White
61->80 alternate odd/even
RC510
1SNA231136R1700
White
81->100 alternate odd/even
RC510
1SNA231137R1000
White

Pkg

Weightcard(1 card) g

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

5
5
5
5
5

5.50
5.50
5.50
5.50
5.50

Continue on next page →1SNC160141S0201

5

Color

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC510 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - vertical mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA231180R2000
1SNA231181R1500
1SNA231182R1600
1SNA231183R1700
1SNA231184R1000
1SNA231185R1100
1SNA231186R1200
1SNA231187R1300
1SNA231188R2400
1SNA231189R2500
1SNA231190R2200
1SNA231191R1700
1SNA231192R1000
1SNA231193R1100
1SNA231194R1200
1SNA231195R1300
1SNA231196R1400
1SNA231197R1500
1SNA231198R2600
1SNA231199R2700
1SNA231200R1400
1SNA231201R0100
1SNA231202R0200
1SNA231203R0300
1SNA231204R0400
1SNA231205R0500

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50
5.50

5

1SNC160141S0201

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

PAGE 131

RC610 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - horizontal mounting
Description–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp, distribution and ADO System®
terminal blocks, and Miniblocks (MS..), from the SNA and Solution series.

Horizontal terminal blockassembly5

Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
201->210 (x10)White
211->220 (x10)White
221->230 (x10)White
231->240 (x10)White
241->250 (x10)White
251->260 (x10)White261->270 (x10)White271->280 (x10)White281->290 (x10)White291->300 (x10)White
301->310 (x10)White311->320 (x10)White
321->330 (x10)White
331->340 (x10)White341->350 (x10)White351->360 (x10)White361->370 (x10)White371->380 (x10)White381->390 (x10)White391->400 (x10)White
401->410 (x10)White411->420 (x10)White421->430 (x10)White431->440 (x10)White441->450 (x10)White451->460 (x10)White461->470 (x10)White471->480 (x10)White481->490 (x10)White491->500 (x10)
White

Type

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

Part Number

1SNA233001R2600
1SNA233002R2700
1SNA233003R2000
1SNA233004R2100
1SNA233005R2200
1SNA233006R2300
1SNA233007R2400
1SNA233008R0500
1SNA233009R0600
1SNA233010R2200
1SNA233011R1700
1SNA233012R1000
1SNA233013R1100
1SNA233014R1200
1SNA233015R1300
1SNA233016R1400
1SNA233017R1500
1SNA233018R2600
1SNA233019R2700
1SNA233020R2400
1SNA233021R1100
1SNA233022R1200
1SNA233023R1300
1SNA233024R1400
1SNA233025R1500
1SNA233026R1600
1SNA233027R1700
1SNA233028R2000
1SNA233029R2100
1SNA233090R2300
1SNA233091R1000
1SNA233092R1100
1SNA233093R1200
1SNA233094R1300
1SNA233095R1400
1SNA233096R1500
1SNA233097R1600
1SNA233098R2700
1SNA233099R2000
1SNA233100R0200
1SNA233101R2700
1SNA233102R2000
1SNA233103R2100
1SNA233104R2200
1SNA233105R2300
1SNA233106R2400
1SNA233107R2500
1SNA233108R0600
1SNA233109R0700
1SNA233110R2300
1SNA233120R2500

Pkg

Weightcard(1 card) g

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160142S0201

1SNC160191F0014

Main technical data

RC610 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233030R2600
1SNA233031R1300
1SNA233032R1400
1SNA233033R1500
1SNA233034R1600
1SNA233035R1700
1SNA233036R1000
1SNA233074R2600
1SNA233075R2700
1SNA233076R2000

5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

Card with 100 markers, repeated identical numbers
0 (x100)
1 (x100)
2 (x100)
3 (x100)
4 (x100)
5 (x100)
6 (x100) / 9 (x100)
7 (x100)
8 (x100)
10 (x100)
11 (x100)
12 (x100)
13 (x100)
14 (x100)
15 (x100)
16 (x100)
17 (x100)
18 (x100)
19 (x100)
20 (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233201R0300
1SNA233202R0400
1SNA233203R0500
1SNA233204R0600
1SNA233205R0700
1SNA233206R0000
1SNA233207R0100
1SNA233208R1200
1SNA233209R1300
1SNA233211R2400
1SNA233212R2500
1SNA233213R2600
1SNA233214R2700
1SNA233215R2000
1SNA233216R2100
1SNA233217R2200
1SNA233218R0300
1SNA233219R0400
1SNA233220R0100
1SNA233221R2600

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

Card with 100 markers, alternate odd/even numbers for double deck terminal blocks
1->20 alternate odd/even
White
RC610
1SNA233133R1600
21->40 alternate odd/even
White
RC610
1SNA233134R1700
41->60 alternate odd/even
White
RC610
1SNA233135R1000
61->80 alternate odd/even
White
RC610
1SNA233136R1100
81->100 alternate odd/even
White
RC610
1SNA233137R1200

5
5
5
5
5

6.80
6.80
6.80
6.80
6.80

Card with 100 markers, ascending order repeated 10 times
1->9+blank (x10)
White

RC610

1SNA233142R2700

5

6.80

Card with 100 markers, ascending order repeated twice (from 1 to 50)
1->50 (x2)
RC610
White

1SNA233141R2600

5

6.80

Continue on next page →PAGE 1335

1SNC160142S0201

Card with 100 markers, ascending order
1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900
901->1000

RC610 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g

5

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233150R0300
1SNA233151R2000
1SNA233152R2100
1SNA233153R2200
1SNA233154R2300
1SNA233155R2400
1SNA233156R2500
1SNA233157R2600
1SNA233158R0700
1SNA233159R0000
1SNA233160R0500
1SNA233161R2200
1SNA233162R2300
1SNA233163R2400
1SNA233164R2500
1SNA233165R2600
1SNA233166R2700
1SNA233167R2000
1SNA233168R0100
1SNA233169R0200
1SNA233170R0700
1SNA233171R2400
1SNA233172R2500
1SNA233173R2600
1SNA233174R2700
1SNA233175R2000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

Card with 100 markers, repeated identical symbols+ (x100)- (x100)= (x100)~ (x100)(x100)

White
White
White
White
White

RC610
RC610
RC610
RC610
RC610

1SNA233111R1000
1SNA233112R1100
1SNA233113R1200
1SNA233114R1300
1SNA233115R1400

5
5
5
5
5

6.80
6.80
6.80
6.80
6.80

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)
White

RC610

1SNA233131R1400

5

6.80

Card with 100 markers, repeated identical symbols
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)

RC610
RC610
RC610
RC610

1SNA233116R1500
1SNA233117R1600
1SNA233118R2700
1SNA233119R2000

5
5
5
5

6.80
6.80
6.80
6.80

RC610

1SNA233132R1500

5

6.80

White
White
White
White

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)White

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160142S0201← Continuation of previous page

RC610 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - vertical mounting

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp, distribution and ADO System®
terminal blocks, and Miniblocks (MS..), from the SNA and Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100) / 9 (x100)
White
7 (x100)
White
8 (x100)White
10 (x100)White
11 (x100)White
12 (x100)White
13 (x100)White
14 (x100)White
15 (x100)White
16 (x100)White
17 (x100)White
18 (x100)White
19 (x100)White
20 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233040R0000
1SNA233041R2500
1SNA233042R2600
1SNA233043R2700
1SNA233044R2000
1SNA233045R2100
1SNA233046R2200
1SNA233047R2300
1SNA233048R0400
1SNA233049R0500
1SNA233050R0200
1SNA233051R2700
1SNA233080R2100
1SNA233081R1600
1SNA233082R1700
1SNA233083R1000
1SNA233084R1100
1SNA233085R1200
1SNA233086R1300
1SNA233087R1400
1SNA233088R2500

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233060R0400
1SNA233061R2100
1SNA233062R2200
1SNA233063R2300
1SNA233064R2400
1SNA233065R2500
1SNA233066R2600
1SNA233067R2700
1SNA233068R0000
1SNA233069R0100

5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233240R1500
1SNA233241R0200
1SNA233242R0300
1SNA233243R0400
1SNA233244R0500
1SNA233245R0600
1SNA233246R0700
1SNA233247R0000
1SNA233248R1100
1SNA233250R1700
1SNA233251R0400
1SNA233252R0500
1SNA233253R0600
1SNA233254R0700
1SNA233255R0000
1SNA233256R0100
1SNA233257R0200
1SNA233258R1300
1SNA233259R1400
1SNA233260R1100

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

Continue on next page →PAGE 1355

1SNC160143S0201

1SNC160190F0014

Description

RC610 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - vertical mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80
6.80

5
5
5
5

6.80
6.80
6.80
6.80

1SNC160143S0201

5

Card with 100 markers, alternate odd/even numbers for double deck terminal blocks
1->20 (x100)
RC610
1SNA233143R2000
White
21->40 (x100)
RC610
1SNA233144R2100
White
41->60 (x100)
RC610
1SNA233145R2200
White
61->80 (x100)
RC610
1SNA233146R2300
White
81->100 (x100)
RC610
1SNA233147R2400
White
Card with 100 markers, repeated identical letters
A (x100)
RC610
1SNA233180R2200
White
B (x100)
RC610
1SNA233181R1700
White
C (x100)
RC610
1SNA233182R1000
White
D (x100)
RC610
1SNA233183R1100
White
E (x100)
RC610
1SNA233184R1200
White
F (x100)
RC610
1SNA233185R1300
White
G (x100)
RC610
1SNA233186R1400
White
H (x100)
RC610
1SNA233187R1500
White
I (x100)
RC610
1SNA233188R2600
White
J (x100)
RC610
1SNA233189R2700
White
K (x100)
RC610
1SNA233190R2400
White
L (x100)
RC610
1SNA233191R1100
White
M (x100)
RC610
1SNA233192R1200
White
N (x100)
RC610
1SNA233193R1300
White
O (x100)
RC610
1SNA233194R1400
White
P (x100)
RC610
1SNA233195R1500
White
Q (x100)
RC610
1SNA233196R1600
White
R (x100)
RC610
1SNA233197R1700
White
S (x100)
RC610
1SNA233198R2000
White
T (x100)
RC610
1SNA233199R2100
White
U (x100)
RC610
1SNA233200R1600
White
V (x100)
RC610
1SNA233235R2400
White
W (x100)
RC610
1SNA233236R2500
White
X (x100)
RC610
1SNA233237R2600
White
Y (x100)
RC610
1SNA233238R0700
White
Z (x100)
RC610
1SNA233239R0000
White
Card with 100 markers, repeated identical symbols+24V (x100)
RC610
1SNA233124R1500
White+48V (x100)
RC610
1SNA233125R1600
White-24V (x100)
RC610
1SNA233126R1700
White-48V (x100)
RC610
1SNA233127R1000White

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC810 terminal block markers
Pre-printed markers for SNA and Solution series

8 mm 0.315 in spacing - horizontal mounting
Description

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, ascending order repeated 10 times
1->9+blank (x10)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA234001R2700
1SNA234002R2000
1SNA234003R2100
1SNA234004R2200
1SNA234005R2300
1SNA234006R2400
1SNA234007R2500
1SNA234008R0600
1SNA234009R0700
1SNA234010R2300
1SNA234011R1000
1SNA234012R1100
1SNA234013R1200
1SNA234014R1300
1SNA234015R1400
1SNA234016R1500
1SNA234017R1600
1SNA234018R2700
1SNA234019R2000
1SNA234020R2500
1SNA234021R1200

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA234030R2700
1SNA234031R1400
1SNA234032R1500
1SNA234033R1600
1SNA234034R1700
1SNA234035R1000
1SNA234036R1100
1SNA234037R1200
1SNA234038R2300
1SNA234039R2400

5
5
5
5
5
5
5
5
5
5

7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20

RC810

1SNA234130R2000

5

7.20

5

Continue on next page →1SNC160144S0201

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp, distribution, power and ADO
System® terminal blocks, and screw clamp Miniblocks, from the SNA and Solution series.

PAGE 137

RC810 terminal block markers
Pre-printed markers for SNA and Solution series

8 mm 0.315 in spacing - horizontal mounting
Description–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp, distribution, power and ADO
System® terminal blocks, and screw clamp Miniblocks, from the SNA and Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA234150R0400
1SNA234151R2100
1SNA234152R2200
1SNA234153R2300
1SNA234154R2400
1SNA234155R2500
1SNA234156R2600
1SNA234157R2700
1SNA234158R0000
1SNA234159R0100
1SNA234160R0600
1SNA234161R2300
1SNA234162R2400
1SNA234163R2500
1SNA234164R2600
1SNA234165R2700
1SNA234166R2000
1SNA234167R2100
1SNA234168R0200
1SNA234169R0300
1SNA234170R0000
1SNA234171R2500
1SNA234172R2600
1SNA234173R2700
1SNA234174R2000
1SNA234175R2100

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20

Card with 100 markers, repeated identical symbols+ (x100)- (x100)= (x100)~ (x100)(x100)

White
White
White
White
White

RC810
RC810
RC810
RC810
RC810

1SNA234111R1100
1SNA234112R1200
1SNA234113R1300
1SNA234114R1400
1SNA234115R1500

5
5
5
5
5

7.20
7.20
7.20
7.20
7.20

RC810

1SNA234116R1600

5

7.20

Card with 100 markers, 5 different symbols repeated 20 times
U-V-W-N-PE (x20)White

1SNC160144S0201

5

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC810 terminal block markers
Pre-printed markers for SNA and Solution series

8 mm 0.315 in spacing - vertical mounting

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp, distribution, power and ADO
System® terminal blocks, and screw clamp Miniblocks, from the SNA and Solution series.

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White
K (x100)
White
L (x100)
White
M (x100)
White
N (x100)
White
O (x100)
White
P (x100)
White
Q (x100)
White
R (x100)
White
S (x100)
White
T (x100)
White
U (x100)
White
V (x100)
White
W (x100)
White
X (x100)
White
Y (x100)
White
Z (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA234040R0100
1SNA234041R2600
1SNA234042R2700
1SNA234043R2000
1SNA234044R2100
1SNA234045R2200
1SNA234046R2300
1SNA234047R2400
1SNA234048R0500
1SNA234049R0600
1SNA234050R0300
1SNA234051R2000
1SNA234052R2100
1SNA234053R2200
1SNA234054R2300
1SNA234055R2400
1SNA234056R2500
1SNA234057R2600
1SNA234058R0700
1SNA234059R0000
1SNA234072R2500

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA234060R0500
1SNA234061R2200
1SNA234062R2300
1SNA234063R2400
1SNA234064R2500
1SNA234065R2600
1SNA234066R2700
1SNA234067R2000
1SNA234068R0100
1SNA234069R0200

5
5
5
5
5
5
5
5
5
5

7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA234180R2300
1SNA234181R1000
1SNA234182R1100
1SNA234183R1200
1SNA234184R1300
1SNA234185R1400
1SNA234186R1500
1SNA234187R1600
1SNA234188R2700
1SNA234189R2000
1SNA234190R2500
1SNA234191R1200
1SNA234192R1300
1SNA234193R1400
1SNA234194R1500
1SNA234195R1600
1SNA234196R1700
1SNA234197R1000
1SNA234198R2100
1SNA234199R2200
1SNA234200R1700
1SNA234201R0400
1SNA234202R0500
1SNA234203R0600
1SNA234204R0700
1SNA234205R0000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20
7.20

PAGE 1395

1SNC160145S0201

1SNC160190F0014

Description

RC1010 terminal block markers
Pre-printed markers for SNA and Solution series

10 mm 0.394 in spacing - horizontal mounting
Description

1SNC160191F0014–– Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp and distribution terminal
blocks from the SNA and Solution series.

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Card with 80 markers, ascending order repeated 10 times
0->7 (x10)White
1->8 (x10)White
9->16 (x10)White
17->24 (x10)White
25->32 (x10)White
33->40 (x10)White
41->48 (x10)White
49->56 (x10)White
57->64 (x10)White
65->72 (x10)White
73->80 (x10)White
81->88 (x10)White
89->96 (x10)White
97->104 (x10)White
105->112 (x10)White
113->120 (x10)White
121->128 (x10)White
129->136 (x10)White
137->144 (x10)White
145->152 (x10)White
153->160 (x10)White
161->168 (x10)White
169->176 (x10)White
177->184 (x10)White
185->192 (x10)White
193->200 (x10)White
Card with 80 markers, ascending order
1->80
White
81->160
White
161->240White
241->320White
321->400
White
401->480
White
481->560
White
561->640
White641->720
White
721->800
White
801->880
White
881->960
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010

1SNA238001R0300
1SNA238002R0400
1SNA238003R0500
1SNA238004R0600
1SNA238005R0700
1SNA238006R0000
1SNA238007R0100
1SNA238008R1200
1SNA238009R1300
1SNA238010R0700
1SNA238011R2400
1SNA238012R2500
1SNA238013R2600
1SNA238014R2700
1SNA238015R2000
1SNA238016R2100
1SNA238017R2200
1SNA238018R0300
1SNA238019R0400
1SNA238020R0100
1SNA238021R2600
1SNA238022R2700
1SNA238023R2000
1SNA238024R2100
1SNA238025R2200
1SNA238026R2300

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00

RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010

1SNA238030R0300
1SNA238031R2000
1SNA238032R2100
1SNA238033R2200
1SNA238034R2300
1SNA238035R2400
1SNA238036R2500
1SNA238037R2600
1SNA238038R0700
1SNA238039R0000
1SNA238040R1500
1SNA238041R0200

5
5
5
5
5
5
5
5
5
5
5
5

8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00

1SNC160146S0201

5

Color

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRC1010 terminal block markers
Pre-printed markers for SNA and Solution series

10 mm 0.394 in spacing - vertical mounting

Vertical terminal blockassembly–– Save printing time with our large pre-printed cards offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp, spring loaded screw clamp, spring clamp and distribution terminal
blocks from the SNA and Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 80 markers, ascending order repeated 10 times
0->7 (x10)White
1->8 (x10)White
9->16 (x10)White
17->24 (x10)White
25->32 (x10)White
33->40 (x10)White
41->48 (x10)White
49->56 (x10)White
57->64 (x10)White
65->72 (x10)White
73->80 (x10)White
81->88 (x10)White
89->96 (x10)White
97->104 (x10)White
105->112 (x10)White
113->120 (x10)White
121->128 (x10)White
129->136 (x10)White
137->144 (x10)White
145->152 (x10)White
153->160 (x10)White
161->168 (x10)White
169->176 (x10)White
177->184 (x10)White
185->192 (x10)White
193->200 (x10)White
Card with 80 markers, ascending order
1->80
White
81->160
White
161->240White
241->320White
321->400
White
401->480
White
481->560
White
561->640
White641->720
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010

1SNA238050R1700
1SNA238051R0400
1SNA238052R0500
1SNA238053R0600
1SNA238054R0700
1SNA238055R0000
1SNA238056R0100
1SNA238057R0200
1SNA238058R1300
1SNA238059R1400
1SNA238060R1100
1SNA238061R0600
1SNA238062R0700
1SNA238063R0000
1SNA238064R0100
1SNA238065R0200
1SNA238066R0300
1SNA238067R0400
1SNA238068R1500
1SNA238069R1600
1SNA238070R1300
1SNA238071R0000
1SNA238072R0100
1SNA238073R0200
1SNA238074R0300
1SNA238075R0400

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00

RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010

1SNA238080R0600
1SNA238081R2300
1SNA238082R2400
1SNA238083R2500
1SNA238084R2600
1SNA238085R2700
1SNA238086R2000
1SNA238087R2100
1SNA238088R0200

5
5
5
5
5
5
5
5
5

8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00
8.00

5

1SNC160147S0201

1SNC160190F0014

Description

PAGE 141

RC55 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - horizontal mounting
Description

Horizontal terminal blockassembly

5

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100) / 9 (x100)
White
7 (x100)
White
8 (x100)White
10 (x100)White
11 (x100)White
12 (x100)White
13 (x100)White
14 (x100)White
15 (x100)White
16 (x100)White
17 (x100)White
18 (x100)White
19 (x100)White
20 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230001R0700
1SNA230002R0000
1SNA230003R0100
1SNA230004R0200
1SNA230005R0300
1SNA230006R0400
1SNA230007R0500
1SNA230008R1600
1SNA230009R1700
1SNA230010R0300
1SNA230011R2000
1SNA230012R2100
1SNA230013R2200
1SNA230014R2300
1SNA230015R2400
1SNA230016R2500
1SNA230017R2600
1SNA230018R0700
1SNA230019R0000
1SNA230020R0500
1SNA230021R2200

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230030R0700
1SNA230031R2400
1SNA230032R2500
1SNA230033R2600
1SNA230034R2700
1SNA230035R2000
1SNA230036R2100
1SNA230037R2200
1SNA230038R0300
1SNA230039R0400

5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230240R2600
1SNA230241R1300
1SNA230242R1400
1SNA230243R1500
1SNA230244R1600
1SNA230245R1700
1SNA230246R1000
1SNA230247R1100
1SNA230248R2200
1SNA230250R2000
1SNA230251R1500
1SNA230252R1600
1SNA230253R1700
1SNA230254R1000
1SNA230255R1100
1SNA230256R1200
1SNA230257R1300
1SNA230258R2400
1SNA230259R2500
1SNA230260R2200

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

Continue on next page →INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160148S0201

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp and spring clamp terminal blocks, and all Miniblocks, from the SNA and
Solution series.

RC55 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230150R1400
1SNA230151R0100
1SNA230152R0200
1SNA230153R0300
1SNA230154R0400
1SNA230155R0500
1SNA230156R0600
1SNA230157R0700
1SNA230158R1000
1SNA230159R1100
1SNA230160R1600
1SNA230161R0300
1SNA230162R0400
1SNA230163R0500
1SNA230164R0600
1SNA230165R0700
1SNA230166R0000
1SNA230167R0100
1SNA230168R1200
1SNA230169R1300
1SNA230170R1000
1SNA230171R0500
1SNA230172R0600
1SNA230173R0700
1SNA230174R0000
1SNA230175R0100

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

Card with 100 markers, repeated identical symbols+ (x100)- (x100)= (x100)~ (x100)(x100)

White
White
White
White
White

RC55
RC55
RC55
RC55
RC55

1SNA230111R2100
1SNA230112R2200
1SNA230113R2300
1SNA230114R2400
1SNA230115R2500

5
5
5
5
5

2.70
2.70
2.70
2.70
2.70

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)
White

RC55

1SNA230131R2500

5

2.70

Card with 100 markers, repeated identical symbols
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)

RC55
RC55
RC55
RC55

1SNA230116R2600
1SNA230117R2700
1SNA230118R0000
1SNA230119R0100

5
5
5
5

2.70
2.70
2.70
2.70

White
White
White
White

5

1SNC160148S0201

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

PAGE 143

RC55 terminal block markers
Pre-printed markers for SNA and Solution series

5 mm 0.197 in spacing - vertical mounting

1SNC160190F0014

Description

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp and spring clamp terminal blocks, and all Miniblocks, from the SNA and
Solution series.

Main technical data
Material
Polyamide

Flammability
V2

Description

5

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical letters
A (x100)
White
B (x100)
White
C (x100)
White
D (x100)
White
E (x100)
White
F (x100)
White
G (x100)
White
H (x100)
White
I (x100)
White
J (x100)
White
K (x100)
White
L (x100)
White
M (x100)
White
N (x100)
White
O (x100)
White
P (x100)
White
Q (x100)
White
R (x100)
White
S (x100)
White
T (x100)
White
U (x100)
White
V (x100)
White
W (x100)
White
X (x100)
White
Y (x100)
White
Z (x100)White

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSTypePart Number

Pkg

Weightcard(1 card) g

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230040R1100
1SNA230041R0600
1SNA230042R0700
1SNA230043R0000
1SNA230044R0100
1SNA230045R0200
1SNA230046R0300
1SNA230047R0400
1SNA230048R1500
1SNA230049R1600
1SNA230050R1300
1SNA230051R0000
1SNA230052R0100
1SNA230053R0200
1SNA230054R0300
1SNA230055R0400
1SNA230056R0500
1SNA230057R0600
1SNA230058R1700
1SNA230059R1000
1SNA230072R0500

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230060R1500
1SNA230061R0200
1SNA230062R0300
1SNA230063R0400
1SNA230064R0500
1SNA230065R0600
1SNA230066R0700
1SNA230067R0000
1SNA230068R1100
1SNA230069R1200

5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA230180R0300
1SNA230181R2000
1SNA230182R2100
1SNA230183R2200
1SNA230184R2300
1SNA230185R2400
1SNA230186R2500
1SNA230187R2600
1SNA230188R0700
1SNA230189R0000
1SNA230190R0500
1SNA230191R2200
1SNA230192R2300
1SNA230193R2400
1SNA230194R2500
1SNA230195R2600
1SNA230196R2700
1SNA230197R2000
1SNA230198R0100
1SNA230199R0200
1SNA230200R2700
1SNA230201R1400
1SNA230202R1500
1SNA230203R1600
1SNA230204R1700
1SNA230205R1000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70
2.70

1SNC160149S0201

Ordering details

RC65 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - horizontal mounting
Description

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100) / 9 (x100)
White
7 (x100)
White
8 (x100)White
10 (x100)White
11 (x100)White
12 (x100)White
13 (x100)White
14 (x100)White
15 (x100)White
16 (x100)White
17 (x100)White
18 (x100)White
19 (x100)White
20 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232001R2500
1SNA232002R2600
1SNA232003R2700
1SNA232004R2000
1SNA232005R2100
1SNA232006R2200
1SNA232007R2300
1SNA232008R0400
1SNA232009R0500
1SNA232010R2100
1SNA232011R1600
1SNA232012R1700
1SNA232013R1000
1SNA232014R1100
1SNA232015R1200
1SNA232016R1300
1SNA232017R1400
1SNA232018R2500
1SNA232019R2600
1SNA232020R2300
1SNA232021R1000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232030R2500
1SNA232031R1200
1SNA232032R1300
1SNA232033R1400
1SNA232034R1500
1SNA232035R1600
1SNA232036R1700
1SNA232037R1000
1SNA232038R2100
1SNA232039R2200

5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232201R0200
1SNA232202R0300
1SNA232203R0400
1SNA232204R0500
1SNA232205R0600
1SNA232206R0700
1SNA232207R0000
1SNA232208R1100
1SNA232209R1200
1SNA232211R2300
1SNA232212R2400
1SNA232213R2500
1SNA232214R2600
1SNA232215R2700
1SNA232216R2000
1SNA232217R2100
1SNA232218R0200
1SNA232219R0300
1SNA232220R0000
1SNA232221R2500

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

Continue on next page →PAGE 1455

1SNC160150S0201

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp and spring clamp (side mounting) terminal blocks, and all Miniblocks
from the SNA and Solution series.

RC65 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - horizontal mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g

5

Card with 100 markers, alternate odd/even numbers for double deck terminal blocks
1->20 alternate odd/even
RC65
1SNA232133R1500
White
21->40 alternate odd/even
RC65
1SNA232134R1600
White
41->60 alternate odd/even
RC65
1SNA232135R1700
White
61->80 alternate odd/even
RC65
1SNA232136R1000
White
81->100 alternate odd/even
RC65
1SNA232137R1100
White

5
5
5
5
5

3.50
3.50
3.50
3.50
3.50

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232150R0200
1SNA232151R2700
1SNA232152R2000
1SNA232153R2100
1SNA232154R2200
1SNA232155R2300
1SNA232156R2400
1SNA232157R2500
1SNA232158R0600
1SNA232159R0700
1SNA232160R0400
1SNA232161R2100
1SNA232162R2200
1SNA232163R2300
1SNA232164R2400
1SNA232165R2500
1SNA232166R2600
1SNA232167R2700
1SNA232168R0000
1SNA232169R0100
1SNA232170R0600
1SNA232171R2300
1SNA232172R2400
1SNA232173R2500
1SNA232174R2600
1SNA232175R2700

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

Card with 100 markers, repeated identical symbols+ (x100)- (x100)= (x100)~ (x100)(x100)

White
White
White
White
White

RC65
RC65
RC65
RC65
RC65

1SNA232111R1700
1SNA232112R1000
1SNA232113R1100
1SNA232114R1200
1SNA232115R1300

5
5
5
5
5

3.50
3.50
3.50
3.50
3.50

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)
White

RC65

1SNA232131R1300

5

3.50

Card with 100 markers, repeated identical symbols
L1 (x100)
L2 (x100)
L3 (x100)PE (x100)

RC65
RC65
RC65
RC65

1SNA232116R1400
1SNA232117R1500
1SNA232118R2600
1SNA232119R2700

5
5
5
5

3.50
3.50
3.50
3.50

RC65

1SNA232132R1400

5

3.50

White
White
White
White

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)White

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160150S0201← Continuation of previous page

RC65 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - vertical mounting

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp and spring clamp (side mounting) terminal blocks, and all Miniblocks
from the SNA and Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White
901->1000
White
Card with 100 markers, repeated identical numbers
0 (x100)White
1 (x100)White
2 (x100)White
3 (x100)
White
4 (x100)
White
5 (x100)
White
6 (x100) / 9 (x100)
White
7 (x100)
White
8 (x100)White
10 (x100)White
11 (x100)White
12 (x100)White
13 (x100)White
14 (x100)White
15 (x100)White
16 (x100)White
17 (x100)White
18 (x100)White
19 (x100)White
20 (x100)
White

Type

Part Number

Pkg

Weightcard(1 card) g

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232040R0700
1SNA232041R2400
1SNA232042R2500
1SNA232043R2600
1SNA232044R2700
1SNA232045R2000
1SNA232046R2100
1SNA232047R2200
1SNA232048R0300
1SNA232049R0400
1SNA232050R0100
1SNA232051R2600
1SNA232052R2700
1SNA232053R2000
1SNA232054R2100
1SNA232055R2200
1SNA232056R2300
1SNA232057R2400
1SNA232058R0500
1SNA232059R0600
1SNA232072R2300

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232060R0300
1SNA232061R2000
1SNA232062R2100
1SNA232063R2200
1SNA232064R2300
1SNA232065R2400
1SNA232066R2500
1SNA232067R2600
1SNA232068R0700
1SNA232069R0000

5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232240R1400
1SNA232241R0100
1SNA232242R0200
1SNA232243R0300
1SNA232244R0400
1SNA232245R0500
1SNA232246R0600
1SNA232247R0700
1SNA232248R1000
1SNA232250R1600
1SNA232251R0300
1SNA232252R0400
1SNA232253R0500
1SNA232254R0600
1SNA232255R0700
1SNA232256R0000
1SNA232257R0100
1SNA232258R1200
1SNA232259R1300
1SNA232260R1000

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

Continue on next page →PAGE 1475

1SNC160151S0201

1SNC160190F0014

DescriptionRC65 terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in spacing - vertical mounting
Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g← Continuation of previous page
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White
White

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232180R2100
1SNA232181R1600
1SNA232182R1700
1SNA232183R1000
1SNA232184R1100
1SNA232185R1200
1SNA232186R1300
1SNA232187R1400
1SNA232188R2500
1SNA232189R2600
1SNA232190R2300
1SNA232191R1000
1SNA232192R1100
1SNA232193R1200
1SNA232194R1300
1SNA232195R1400
1SNA232196R1500
1SNA232197R1600
1SNA232198R2700
1SNA232199R2000
1SNA232200R1500
1SNA232235R2300
1SNA232236R2400
1SNA232237R2500
1SNA232238R0600
1SNA232239R0700

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50
3.50

1SNC160151S0201

5

Card with 100 markers, repeated identical letters
A (x100)
B (x100)
C (x100)
D (x100)
E (x100)
F (x100)
G (x100)
H (x100)
I (x100)
J (x100)
K (x100)
L (x100)
M (x100)
N (x100)
O (x100)
P (x100)
Q (x100)
R (x100)
S (x100)
T (x100)
U (x100)
V (x100)
W (x100)
X (x100)
Y (x100)
Z (x100)

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRCAL85 terminal block markers
Pre-printed markers for SNA and Solution series

8 mm 0.315 in spacing - horizontal mounting
Description

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)
White

RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85

1SNA237001R2200
1SNA237002R2300
1SNA237003R2400
1SNA237004R2500
1SNA237005R2600
1SNA237006R2700
1SNA237007R2000
1SNA237008R0100
1SNA237009R0200
1SNA237010R2600
1SNA237011R1300
1SNA237012R1400
1SNA237013R1500
1SNA237014R1600
1SNA237015R1700
1SNA237016R1000
1SNA237017R1100
1SNA237018R2200
1SNA237019R2300
1SNA237020R2000
1SNA237021R1500

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90

Card with 100 markers, ascending order
1->100101->200
201->300
301->400
401->500
501->600
601->700
701->800
801->900
901->1000

RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85

1SNA237030R2200
1SNA237031R1700
1SNA237032R1000
1SNA237033R1100
1SNA237034R1200
1SNA237035R1300
1SNA237036R1400
1SNA237074R2200
1SNA237075R2300
1SNA237076R2400

5
5
5
5
5
5
5
5
5
5

2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90

Card with 100 markers, 5 different symbols repeated 20 times
L1-L2-L3-N-PE (x20)
White

RCAL85

1SNA237131R1000

5

2.90

Card with 100 markers, 9 different symbols repeated 10 times
U1-U2-U3-V1-V2-V3-W1-W2-W3 (x10) + U1 (x10)
White

RCAL85

1SNA237132R1100

5

2.90

White
White
White
White
White
White
White
White
White
White

PAGE 149

5

1SNC160152S0201

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark spring clamp terminal blocks and ADO System® Miniblocks from the SNA and Solution
series.

RCAL85 terminal block markers
Pre-printed markers for SNA and Solution series

8 mm 0.315 in spacing - vertical mounting

1SNC160190F0014

Description

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark spring clamp terminal blocks and ADO System® Miniblocks from the SNA and Solution
series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Card with 100 markers, ascending order repeated 10 times
0->9 (x10)White
1->10 (x10)White
11->20 (x10)White
21->30 (x10)White
31->40 (x10)White
41->50 (x10)White
51->60 (x10)White
61->70 (x10)White
71->80 (x10)White
81->90 (x10)White
91->100 (x10)White
101->110 (x10)White
111->120 (x10)White
121->130 (x10)White
131->140 (x10)White
141->150 (x10)White
151->160 (x10)White
161->170 (x10)White
171->180 (x10)White
181->190 (x10)White
191->200 (x10)White
Card with 100 markers, ascending order
1->100White
101->200
White
201->300
White
301->400
White
401->500
White
501->600
White
601->700
White
701->800
White
801->900
White

Type

Part Number

Pkg

Weightcard(1 card) g

RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85

1SNA237040R0400
1SNA237041R2100
1SNA237042R2200
1SNA237043R2300
1SNA237044R2400
1SNA237045R2500
1SNA237046R2600
1SNA237047R2700
1SNA237048R0000
1SNA237049R0100
1SNA237050R0600
1SNA237051R2300
1SNA237080R2500
1SNA237081R1200
1SNA237082R1300
1SNA237083R1400
1SNA237084R1500
1SNA237085R1600
1SNA237086R1700
1SNA237087R1000
1SNA237088R2100

5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5
5

2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90

RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85

1SNA237060R0000
1SNA237061R2500
1SNA237062R2600
1SNA237063R2700
1SNA237064R2000
1SNA237065R2100
1SNA237066R2200
1SNA237067R2300
1SNA237068R0400

5
5
5
5
5
5
5
5
5

2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90
2.90

1SNC160153S0201

5

Color

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSRCT terminal block markers
Pre-printed markers for SNA and Solution series

Vertical terminal blockassembly–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– Card with 100 markers, ascending order.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g

6 mm 0.236 in spacing
RCT610To be used to top mark MA2,5/5-CPE.., screw clamp, ADO System® and spring loaded screw clamp (top marking) terminal
blocks from the SNA and Solution series.
1 -> 100
RCT610
1SNA236001R2100
5
6.00
White

8 mm 0.315 in spacing
RCT810To be used to mark 9.5 mm 0.374 in or 12.5 mm 0.492 in spacing screw clamp (top marking), ADO System®, spring loaded
screw clamp and ring lug terminal blocks from the SNA and Solution series.
1 -> 100
RCT810
1SNA236501R2300
5
8.00
White

5

1SNC160155S0201

1SNC160190F0014

Description

PAGE 151

RTM terminal block markers
Pre-printed markers for SNA and Solution series

6 mm 0.236 in to 12 mm 0.472 in spacing - top marking
Description

1SNC160193F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark screw clamp and ADO System® terminal blocks from the SNA and Solution series,–– Spacing corresponds to the pitch between numbers.

RTM7

Main technical data
Material

Flammability

PVC

V0

Ordering details
Length
mm

1 2 3

49 50

1

2

50

1

2

50

Color

Type

Part Number

Pkg

Weightcard(1 card) g

6 mm 0.236 in spacing
1 marking strip with black print from 1 to 50 on one side and 51 to 100 on the other side300
RTM7
1SNA103115R1300
White

1

1.00

1

1.00

1

1.00

8 mm 0.315 in spacing
1 marking strip with black print from 1 to 50 on one side and 51 to 100 on the other side
400
RTM7
1SNA103116R1400
White

10 mm 0.394 in spacing
1 marking strip with black print from 1 to 50 on one side and 51 to 100 on the other side
500
RTM7
1SNA103922R1400
White

1SNC160156S0201

5

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSREH3 terminal block markers
Pre-printed markers for Solution series
Description

Horizontal terminal blockassembly

Main technical data
Material

Flammability

Cellulose acetate

V2

Ordering details
Description

Color

Type

Card with 680 precut labels with numbers - Red print on white background
6 series from 1 to 102 + 1 series from 103 to 170
REH3
Red
22 series from 1 to 30 + 1 series from 1 to 20
REH3
Red

Part Number

1SNA163167R2200
1SNA164695R2500

Pkg

Weightcard(1 card) g

1
1

20.00
20.00

5

1SNC160154S0201

1SNC160191F0014–– Save printing time with our large pre-printed card offer with pre-printed numbers, letters or symbols,–– To be used to mark 13 mm 0.512 in or 16 mm 0.630 in spacing ring lug terminal blocks from the Solution
series,–– Red print on white background (black print on white background on request).

PAGE 153

EPU terminal block markers
Pre-printed cover marker for SNA series

5 mm 0.197 in to 12 mm 0.472 in spacing - top marking

1SNC700193F0000

Description

EPU5–– Protective label used to indicate live circuits,–– Prohibits access to connection screws,–– To be snapped directly onto the terminal block,–– To be used to cover one single screw clamp terminal block from the SNA and Solution series.

Main technical data
Material

Flammability

Polyamide

V2

Ordering details
Description

Color

Type

Part Number

Pkg

Weightcard(1 card) g

5 mm 0.197 in spacing
EPU5
For MA2,5/5 SNA terminal blocks
Yellow label with black arrow

1SNA107033R1000

1

2.00

For M4/6, M6/8, M10/10 and M16/12 SNA terminal blocks (use two labels for M16/12)
Yellow label with black arrow
EPU6
1SNA107038R2500
Yellow

1

2.00

Yellow

EPU56 mm 0.237 in to 10 mm 0.394 in spacing
EPU6

1SNC160157S0201 - Rev. A

5

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSEP terminal block markers
Pre-printed cover marker for SNA and Solution series

6 mm 0.236 in to 22 mm 0.866 in spacing - top marking

EP–– Yellow label with red arrow, used to indicate live circuits,–– Prohibits access to connection screws and protects connections from dust and from touch,–– To be mounted using 2 nylon VSP screws (ordered separately),–– Can cover 3 or 4 terminal blocks.

Main technical data
Material

Flammability

PVC

V0

Ordering details
Description

Color

EP6
For 4x M4/6, or 3x M6/8 or M6/8.RS terminal blocks

TypePart Number

Pkg

Weightcard(1 card) g

Yellow

EP6

1SNA163427R1700

10

0.41

EP8
For 4x M6/8 or M6/8.RS, or 3x M10/10 or M10/10.RS terminal blocks Yellow

EP8

1SNA163428R2000

10

0.59

EP10
For 4x M10/10 or M10/10.RS, or 3x M16/12 terminal blocks

Yellow

EP10

1SNA163429R2100

10

0.74

EP12
For 4x M16/12 or 3x M35/16 terminal blocks

Yellow

EP12

1SNA163430R2600

10

0.85

EP16
For 4x M35/16 terminal blocks

Yellow

EP16

1SNA163431R1300

10

1.1

EP223
For 3x D70/22 terminal blocks

Yellow

EP223

1SNA173327R2400

10

EP224
For 4x D70/22 terminal blocks

Yellow

EP224

1SNA173328R0500

10

10.00

VSP6
VSP12
VSP16
VSP68
VSP22

1SNA163433R1500
1SNA163432R1400
1SNA173147R2000
1SNA206103R0700
1SNA400252R1200

20
20
20
20
20

0.21
0.1
0.3
0.6
0.25

5

Compatible screws
Nylon screw
Nylon screw
Nylon screw
Nylon screw
Nylon screw

Selection guide for cover and fixing screw depending on terminal block type
Terminal block

3 terminal blocks aligned

4 terminal blocks aligned

Screws for protection label

Type
M4/6
M6/8
M10/10
M16/12
M35/16
D70/22
M6/8.RS
M10/10.RS

Cover type
–
EP6
EP8
EP10
EP12
EP223
EP6
EP8

Cover type
EP6
EP8
EP10
EP12
EP16
EP224
EP8
EP10

Type
VSP6

Part Number
1SNA163433R1500

VSP12
VSP16
VSP22
VSP68

1SNA163432R1400
1SNA173147R2000
1SNA400252R1200
1SNA206103R0700

Cover part number–
1SNA163427R1700
1SNA163428R2000
1SNA163429R2100
1SNA163430R2600
1SNA173327R2400
1SNA163427R1700
1SNA163428R2000

Cover part number
1SNA163427R1700
1SNA163428R2000
1SNA163429R2100
1SNA163430R2600
1SNA163431R1300
1SNA173328R0500
1SNA163428R2000
1SNA163429R2100

PAGE 155

1SNC160158S0201

1SNC700194F0000

DescriptionOrder form
Customized marking

8 characters max. on MC512PA,
MC612PA, MC812PA
Vertical terminal
block assembly

7 characters max. on RC 410, RC 510,
RC 610, RC 810 and RC 1010 markers
3 characters max. on
RC 55, RC 65 and RCAL 85 markers

4 characters max. on MC812PA
3 characters max. on MC512PA, MC612PA
7 characters max. on RC1010
Horizontal terminal
block assembly

5 characters max. on RC810, RCAL85
3 characters max. on RC510, RC55, RC610, RC65
2 characters max. on RC410

10 strips of 10 markers for SNK series
terminal blocks with 5.2 mm 0.205 in spacing ............

MC 512 PA

10 strips of 10 markers for SNK series
terminal blocks with 6 mm 0.236 in spacing ................

MC 612 PA

10 strips of 10 markers for SNK series
terminal blocks with 8 mm 0.315 in spacing ................

MC 812 PA

10 strips of 10 markers for screw and spring
terminal blocks with 4 mm 0.157 in spacing ................

RC 41010 strips of 10 markers for screw, spring and ADO
terminal blocks with 5 mm 0.197 in spacing.................

RC 51010 strips of 10 markers for screw, spring and ADO
terminal blocks with 6 mm 0.236 in spacing.................

RC 61010 strips of 10 markers for screw, spring and ADO
terminal blocks with 8 mm 0.315 in spacing.................

RC 81010 strips of 8 markers for screw and spring
terminal blocks with 10 mm 0.394 in spacing and above...

RC 101010 strips of 10 markers for screw, spring and ADO
terminal blocks with 5 mm 0.197 in spacing.................

RC 55

10 strips of 10 markers for screw, spring and ADO
terminal blocks with 6 mm 0.236 in spacing.................

RC 65

10 strips of 10 markers for screw, spring and ADO
terminal blocks with 8 mm 0.315 in spacing and above....

RCAL 85

Quantity: ___________________________

Order No.: ___________________________________________
Name: ______________________________________________
Company: ___________________________________________
Delivery address: _________________________________________________________________________________________
Zip code: ___________________ City: ____________________
Tel.: ________________________ Fax: _____________________
E-mail: ______________________________________________For any order, please contact
your local sales agent

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160218S0201

5

TO AVOID ANY ERRORS, PLEASE WRITE VERY CLEARLY

Type of card:

PB1595

PAGE 157

MG3 markers selection guidefor other manufacturers' terminal blocks
Terminal block
MG-CPM terminal block markers are available
in versions to suit the particular terminal blockformats of the most widely used products, seeselection guide to side.

Depending on type, markers are presented asjoined strips at a set or as separate markers
for convenient individual insertion on mixed
spacing terminal block assemblies.

Order form
Customized marking
Markers
Strip markers

Marker spacing
Marker width

Individual markers

Marker spacing
Marker width

Strip mounting (Marker spacing = Terminal block spacing)P - Single clips to spacing

Marker width = Terminal block width
M - Modular strip

Marker width < Terminal block width
CP - Single clips compatible to spacing

Marker width < Terminal block width

Individual mounting (Marker spacing ≠ Terminal block spacing)S - Single clips

Marker width = Terminal block width
C - Single clips compatible

Marker width < Terminal block width

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160219S0201

6

MG3 markers selection guidefor other manufacturers' terminal blocks

M

M
M
M

M

6x10

5x12

4.2x9
MG-CPM-12 46390

5x10
M
M

MG-CPM-10 46192

4.2x9
M

M

5x10

5x12

MG-CPM-12 46390
M

M

MG-CPM-04 41391

6x10

MG-CPM-10 46192

C
S
C M
S
C
S
C
C
S
S
CP
CP
C
C
P

C
P
C
S
S
S
C
C
S
S
C
C
C
C
C
P

S
C
S
C
C
C
C
C
C
C
C
S
C
C
C
C
C
C

S
C
S
C
C
C
C
C
C
C
C
S
C
C
P
P
P
P

C
C
C
C
C
P

P

M
P
C
C
C
C
C
C
C
C
P
C
C
C
C
C
C

6

M

5x12

4.2x9
MG-CPM-12 46390

1SNC160219S0201

5x10

P
P
S
S

MG-CPM-10 41692

P
P
S
S

MG-CPM-04 41395

SS

MG-CPM-04 41340N 5x10

S
S
S
S

MG-CPM-04 41390N 5x10

5x10MG-CPM-03 41293

Terminal block
CDB4/2(1)CMC2-2
CGT6N
CSCG10T

5x10

Marker

MG-CPM-03 41291

Size mm

5x7

Connectwell

MG-CPM-01 41094

Terminal block
CBD.2/4
S
CBD.4/6
C
CBD.2/4/SH
S
CBD.4/6/SH
C
CBD.6/10
C
CBD.10/6
C
CBD. 16/25
C
CBD. 35C
CBC.2/4
P
CBC.4/6
C
CBC 35/50
C
DAS.4/6...DAS.4/6/SS
C
DSS.4/6
C
CBR.2/4
P
FVS.4/6
C
FFS.4/6
C
TLS.2/4
C
TLE.2/4
C
TLD.2/4
C
TDE.2/4
C
PCE.4/6/...
C
PCE.4/X...
C
SFR.4/6...SFR.4/6/C230
C
SFO.4/6...SFO.4/6/C230
C
FPC.10/16
C
FPL.10/16...FPL.10/16/C230
C
SFR.4/D1A...SFR.4/D3A
C
MPS.2/4/SW...MPS.2/4/SV
S
MPS.4/6...MPS.4/6/VS
C
SCB.4/6...SCB.&/10/CD
C
AFO.2/1+1...AFO.2/2+2/TP
C
PDF.2
C
FDP.2
C
CVF.4/6...CVF.4/6/TP
C
TC/PO
S
VPC.2/4
S
VPD.2/
S
GPM.95/BB...GPM.240/300/CC C
GPA.70...GPA.240
C
ACB.70/BB...ACB.185/240/CC C
BCA.70/BB...BCA.120/185/CC C

C
S
C
P
C
P
C
C
P
P
C
C
C
C
C

MG-CPM-04 41390N

5x10

MG-CPM-04 41391

5x10

P
C
P
C
C
C
C
C
S
C
C
C
C
S
C
C
C
C
C
C
C
C
C
C
C
C
C
P
C
C
C
C
C
C
P
S
S
C
C
C
C

5x10

P
C M
S
C M
CP
C
C
C
M S
C M
C
C
C M
M S
C M
C M
C
C
C
C
C M
C
CP
CP M
C
C
CP
S
C
C
C
C
C
C
S
S
S
C
C
C
C

MG-CPM-03 41293

Marker

MG-CPM-03 41291

Size mm

MG-CPM-04 41390N

Cabur

Terminal block
MBL.50/6...MBL.150/12
TEO.2/4
TEO.4/6
CBE.2/4
TE.4/6/D...TE.50/D...TE.50/O
RN.2/4
RP.4/6
RFI.2
TR.2/4TR.4/6
MAC.6/10...MAC.6/10/N
CAM...CAM/C
NCS
NCV
CNT.6...CNT.35
HMM.1/2,5...HMM.1/2,5/2+2
HMM.2/4...HMM.6/10
HTE.2/4...HTE.6/10
HMD.2N...HMD.2/4
HMS.2/4
HMF.4/6...HMF.4/6/L115
EDM.2/4
EDM.4/6...EDM.70/50/BC
SV.2...SV.2/VS
SV.4/6...SV.10/16
CPS.4/6
SCX.10/16...SCX.10/16-PI
SFC.10/16
SFL.10/16
FLD.10/16/F5...FLD.10/16/D
VLM.10/16...VLM.10/16/O
VL.16...VL.16/O-M
TC/DINVNF.6/10...VNF.6/10/STP
CDA.70/BC...CDA.185/BB
BTU
BT/3
BT/2
BT/DIN/PO

5x10

4.2x9
C

MG-CPM-01 41091N 5x15

Terminal block
KL 9010Marker

MG-CPM-01 41090N 5x10MarkerSize mm

MG-CPM-12 46390

Size mm

MG-CPM-03 41293

Cabur

MG-CPM-03 41291

BECKHOFF

M
M

PAGE 159

MG3 markers selection guidefor other manufacturers' terminal blocks

5x12

4.2x9
MG-CPM-12 46390

S
S
S
S
S
S
S
S
S
P
S

5x10

S
S
S
S
S
S
S
S
S
P
S

MG-CPM-10 41692

S
S
S
S
S
S
S
S
S
S
S

MG-CPM-04 41395

5x10MG-CPM-03 41293

MG-CPM-04 41340N 5x10

5x10MG-CPM-03 41291

MG-CPM-04 41390N 5x10

5x7MG-CPM-01 41094

4.2x9

MG-CPM-01 41091N 5x15

5x12MG-CPM-12 46390

MG-CPM-01 41090N 5x10

5x10

S
S
S

S

M

S

M

S

S
S
S
S
S

S

M
M
M
M
M
M
M
M
M

S
S

M

Conta Clip
Size mmMarker

M

M
M

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

Terminal block
PK-TS 15/35
ZRKG
ZSLG
ZSLN
ZSRK
ZVMAK

C
C
C
C
C
C

C
C
C
C
C
C

C
C
C
C
C
C

C
C
C
C
C
C

LegrandSerie Viking 3

MG-CPM-09 41890 5x10 mm white PVC legend

1SNC160219S0201

S
S

M

S
S
S

5x7

S

M

S
S
S

S

MG-CPM-01 41094

S

M

S

S
S
S
S

5x10

S

M

S

S

S
S
S
S

MG-CPM-02 41190N

S

M

S

S
S
S
S

5x15

S

M

Terminal block
CTS25UN
CMDB6/2
CGT35U
CSC16T
CTS95U
CSC10T
CTS35UCTS16UCR
CTS50U
CSFL4U
STH4DT
CDB10/2
ASF4
DDFL4UE24V
CSFL4UL24V
DDDL4U
DDFL4ULRCTS4UNCR
CTS2.5UN
CMDB6/2
CTS2.5M
CTS4SCCTS6
CTS6SCCTSSRN5
CTS10SC
CTS16
CTS10

5x10

S

M

Marker

MG-CPM-01 41091N

S

M
M

Size mm

MG-CPM-01 41090N

S

S
P
P
S
P
S
S
S
P
S
S
P
S
S
S
P
S
S
S
P
S
S
P
S
P
S
S
S
S
S
P
S
S
S
S
S
S
S
S
S
S
S
S
S
S
P
S
S
S
S
P
P
S
S
S
S
S
S
S

MG-CPM-10 41692

5x10
S

S
P
P
S
P
S
S
S
P
S
S
P
S
S
S
P
S
S
S
P
S
S
P
S
P
S
S
S
S
S
P
S
S
S
S
S
S
S
S
S
S
S
S
S
S
P
S
S
S
S
P
P
S
S
S
S
S
S
S

MG-CPM-04 41395

5x10MG-CPM-03 41293
SS

MG-CPM-04 41340N 5x10

5x7MG-CPM-03 41291
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S
S

MG-CPM-04 41390N 5x10

6Terminal block
CGT16N
AS2.5/4
CTU4U
CTS6UCRCTS4UN
CT25UCR
CMDB4/2
CSDL6U
CSC2.5T1-2
AS6
CT25U
CGT4UN
CGT10N
DDFL4UELR24V
DDFL4UEL
CSC2.5T2-2
CTS10U
AS4/3
CTS10USC
AS2.5/3
CENC16
DDFL4U
CTS2.5UNCR
CDTTU
CSC4T1-2
CKT4U
CSC4T2-2
CSCG4T
CTS6U
CSC4T
CSCG2.5T
CSFL6U
CENC35
CGT10UCSDL4U
CSC6T
CGT4U
AS4/4
AS4
CTS4UNCRCTS6USC
STH4
CTS16UCSCG16T
CSC6T1-2
CSC2.5T
ODL4U
CMC1-2
CDB6/2ODL4UA
AS2.5
ADL2.5
CDB25/2
CTS25UCDTTUSH
CTS35UN
CT35UCR
CTS10UCRCMDB10/2

MG-CPM-01 41094

Marker

MG-CPM-01 41091N 5x15

Connectwell
Size mm

MG-CPM-01 41090N 5x10

Connectwell

MG3 markers selection guidefor other manufacturers' terminal blocks

6x10

5x10

MG-CPM-04 41391

MG-CPM-07 41691

C
P
P
P
P
P
P
C
C
C
C
C
C
C
C
C
C
C
C
C
P
C
C
P
P
S
P
P
P
P
S
C
C
C
P
P
P
C
C
C
C
C

P
P
P

M
M
M
M
M
M
M

M

M
M
M C
M
M
M

M C
M C
M C
C

C
C

M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

5X10

6x10

5x10

MG-CPM-04 41391

MG-CPM-07 41691

C
C
C
C
C
C
C
C
C
C
C
C
C
C

C
C
C
C
C
C
C
C
C
C
C
C
C
S
C
C
C
C
C
C
C
C
C
P
P
P
P
P

C
S
S
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
S
C
C
S
S

C
P
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
P
C
C
P
P

C
C
P
P
P
P
P
P
P
C
C
C

M
M
M
M
M

C
C
C
C
C
C
C
C
C
C
C
C
C

M
M
P
P
P
P
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
M

M
M

STF-04 42804 bracket

5x10

C
C
C
C
C
C
C
C
C
C
C
C
C

M
M
M
M
M
M
M
M
M
M
M
M
M

P
P
P
P
P
P

M
M
M
M
M
M
M
M
M
M M
M M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

6

1SNC160219S0201

5X10
MG-CPM-04 41395

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
S
C
C
C
S
S
C
S
S
S
S
C
C
C
S
S
S
C
C
C
C
C

STF-04 42804 bracket

5x10

Terminal block
ASI IO SL DI 4/4
ASI IO SL DIO 4/2/2
ASI IO SL DIO 8/4/4
ASI IO SL DO 4/4
DFK ...
DFK 4
DFK 4 - PE
DFK 4 - SI
DIK 1.5
DIK 1.5 - LA (RD)DIKD 1.5
DIKD 1.5 - LA
DIKD 1.5 - PV
DLK 2.5 - PE
DLKB 2.5 PE
DOK 1.5 - 2D
DOK 1.5 LA
DOK 1.5 TG
DOKD 1.5 - TG
E - UKGBS 5-UK/B
GTF 76/230
IBIL ...
K4 - SPMBK 3/ E - Z
MBK 3/ E - Z -PE
MBK 6 / EMBKKB 2.5
MBKKB 2.5 - DIO
MBKKB 2.5 - PV
MBKKB 2.5 + V
MBT 2.5
MBT 2.5 PE
MSLKG 6
MTK - LOE
MTK - P/P
MTK - TPMTKD-...
OTTA 2.5
OTTA 2.5 PE
OTTA 6OTTA 6 - PE

5x10

Marker

MG-CPM-04 41390N

Size mm

MG-CPM-03 41291

Phoenix Contact

Terminal block
OTTA 6 - T
OTTA 25
PIK 4 -L
PIK 4 - L / L
PIK 4 - L / LB
PIK 4- PE / L / NTPIK 4 - PE / L / NTB
PIK 4 PE / L / L
PIK 4 PE / L / N
PIK 6 - L / L
PIK 6 - PE / L / L
PIK 6 - PE / L / N
PLC RSCPLC BSC
QT 1.5
QT 1.5 TWIN
QT 1.5-PE
RTK
SLKK 5SLKK 5 - LA
SSK 0525 KER-EX
SSK 110 KER-EX
SSK 116 KER-EX
ST……
STU…..
STS…
STI….
STN…
STTB
TML...
UDK 3
UDK 3 - PE
UDK 4
UDK 4 - ILA
UDK 4 - ULA
UDK 4 MTK - P / P
UDK 4 TGUDMTK 5 - P / P
UDMTK 5 - TWIN - P/P
UHSK / S 2000
UHV 25
UHV 50UHV 95
UHV 150
UHV 240UIK 16UIK 16 - PE / N
UIK 35 - PE / N
UIKN 35UISLKG 16UISLKG 35
UK - FRONT 4
UK - FRONT 4 - PE
UK 2.5
UK 2.5 B
UK 2.5 LOER
UK 2.5 N
UK 3MG-CPM-04 41395

S

Marker

5x10

S

Size mm

MG-CPM-04 41390N

Terminal block
Serie EURO

MG-CPM-12 46390

Marker

MG-CPM-01 41090N 5x10Size mm

MG-CPM-03 41291

Phoenix Contact
4.2x9

Morsettitalia

PAGE 161

MG3 markers selection guidefor other manufacturers' terminal blocks

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

6x10

5x10
MG-CPM-07 41691

C
C
S
C
C
C
C
C
C
C
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
S
S
S
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

C
C
C
P
P
C
C
C
C
C
M C
C
C
C
C
C
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
P

P
C
C
C
C
C
C
C
P
P
P
P
P
C
C

M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

1SNC160219S0201

5X10

MG-CPM-04 41391

C
C
S
C
C
C
C
C
C
C
S
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
S
S
S
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

STF-04 42804 bracket

5x10

Terminal block
UKH 150
UKH 240
UKK 3
UKK 4 - FS
UKK 4 - FS / FS
UKK 5
UKK 5 - DIO
UKK 5 - TG
UKK 5 -2 -DIO
UKK 5 -LA
UKKB 3
UKKB 5UKKB 10UKKB 10 / 2.5
UKKB 10 / 2.5 - PE
UKN 2.5
UKN 4
UKN 5
UKN 10 (N)UKN 16
UKN 16N
UKN 35UKSN
URK - ND
URK - ND 2URKNURKN - A
URKN / S
URTK - BEN
URTK / S
URTK / S - BEN
URTK / SS
URTKD / SP
USED 16
USED 27
USEN 14USEN 18
USK / SGSKUSK 4 FSR...
USLKG 2.5
USLKG 2.5 - N
USLKG 3USLKG 4USLKG 5USLKG 10 (N)USLKG 16USLKG 16 N
USLKG 35USLKG 50USLKG 95
UT 4
UT 4 BUUT 4 YE
UT 4-MTD BU
UT 4-MTD-PEUTK 35UXKK 4
VBSN 4 FS ....

MG-CPM-04 41395

P
P
P
P
P
P
P
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

5x10

5x10

M
M
M
M
M
M

MG-CPM-04 41390N

6x10

MG-CPM-07 41691

P
P
P
P
P
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

Marker

MG-CPM-03 41291

5X10

MG-CPM-04 41391

S
S
S
S
S
S
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

Size mm

STF-04 42804 bracket

5x10

MG-CPM-04 41395

6

Terminal block
UK 3 - EX
UK 3 - RETURN
UK 3 - RETURN - PE
UK 3 - TWIN
UK 3 - TWIN - PE
UK 3 N
UK 4
UK 4 - TG
UK 4 - TG -LOER - P/P
UK 4 FS / FS
UK 4 FSR
UK 4 LOER
UK 4 TPUK 4 TP / TP
UK 5
UK 5 - HESIUK 5 - MTK - P/P
UK 5 - R - L
UK 5 - TWIN
UK 5 - TWIN - EX
UK 5 / R - DRAHT
UK 5 N
UK 5 RETURN
UK 5 RETURN - PE
UK 5 TWIN
UK 5 TWIN - PE
UK 6
UK 6 N
UK 6.3 HESI
UK 10
UK 10 - DREHSI
UK 10 - EX
UK 10 - N-PE / N
UK 10 - PLUS
UK 10 - PLUS - PE
UK 10 - TWIN
UK 10 - TWIN - PE
UK 10 NUK 10 RETURN
UK 10 RETURN - PE
UK 10.3 - HESI
UK 16
UK 16 - EX
UK 16 - PE / N
UK 16 NUK 16 N - EX
UK 16 N - PE / N
UK 35
UK 35 - EX
UK 35 - PE / N
UK SI
UKB 4 FS ...
UKD 4 PEUKH 25
UKH 50
UKH 50 - PE / N
UKH 95
UKH 95 - PE / N

5x10

MarkerPhoenix Contact

MG-CPM-04 41390N

Size mm

MG-CPM-03 41291

Phoenix Contact

MG3 markers selection guidefor other manufacturers' terminal blocks

5X10

5x10
MG-CPM-07 41691

STF-04 42804 bracket

5x10

MG-CPM-06 41591

M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

4.2x9

P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P

MG-CPM-12 46390

S
C

5x7

S
C

6

1SNC160219S0201

M
M
M
M
M

C
C

C
C
C
C

5x10

P
S
S
S
S
S

Terminal block
Top-Job 2000
Top-Job 2001
Top-Job 2002
Top-Job 2004
280-520280-560
280-601
280-607280-612280-622280-626
280-641
280-646
280-649
280-650
280-651
280-653
280-654
280-656
280-671
280-672
280-676
280-681280-683
280-684
280-685
280-687
280-695
280-830
280-831280-832
280-833
280-834
280-835

MG-CPM-04 41390N 5x10

5x10MG-CPM-07 41691

P

STF-04 42804 bracket

5X10

Terminal block
8WH…
8WA1 011-0DF21
8WA1 011-0DG21
8WA1 011-1BF23
8WA1 011-1DF11
8WA1 011-1DG11

5x10

Marker

MG-CPM-06 41591

Size mm

MG-CPM-04 41390N

Siemens

Marker

5x10

P

Size mm

MG-CPM-03 41293

P

Wago

MG-CPM-03 41291

P

M
M
M
M
M
M
M

MG-CPM-02 41190N 5x10

P

S
S
S
S
S
S
S
S
S

MG-CPM-01 41094

5x10
MG-CPM-07 41691

6x10
MG-CPM-04 41391

Terminal block
IK...

MG-CPM-04 41395

Marker

MG-CPM-04 41390N 5x10Size mm

5X10

Schlegel

Terminal block
8WA1 011-2DG11
8WA1 011-3DF21
8WA1 011-3DG21
8WA1 011-1DH11
8WA1 221
8WA1 741-2X
8WA2 011-1DF20
8WA2 011-1DG20
8WA2 011-1DH20

MG-CPM-04 41390N

5x10

P
P
P
C
C
C
C
C

M
M
M
M
M M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

MG-CPM-01 41091N 5x15

6x10MG-CPM-07 41691

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

Marker

MG-CPM-01 41090N 5x10

5X10

MG-CPM-04 41391

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

Size mm

STF-04 42804 bracket

5x10

MG-CPM-04 41395

Terminal block
VBST 4 FS / FS
VIOK 1.5
VIOK 1.5-2D
VIOK 1.5-3D/PE
VIOK 1.5-D/TG/D/PE
VIOK 1.5-LA
ZFDK 2.5
ZFDK -PEZFK 2.5 - PEZFK 2.5 - PE / L / N
ZFK 2.5 - TWINZFK 2.5 - TWIN - PE
ZFK 4
ZFK 4 - PEZFK 4 - TG
ZFK 6
ZFK 16ZFK I 4ZFKK 2.5 (-MT)
ZFKN 45x10MarkerSiemens

MG-CPM-04 41390N

Size mm

MG-CPM-03 41291

Phoenix Contact

PAGE 163

MG3 markers selection guidefor other manufacturers' terminal blocks

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

C

4.2x9
MG-CPM-12 46390

5x10
MG-CPM-03 41293

C
C
C
C
C
C
C
C
C

MG-CPM-04 41390N 5x10

5x10MG-CPM-03 41291

5x7

MG-CPM-02 41190N 5x10

MG-CPM-01 41094

Terminal block282-684282-687282-901
282-902282-904
282-907283-602283-604
283-607283-609283-671283-672283-674283-677283-901
283-902283-904
283-907284-601
284-604284-607284-681284-682284-684284-687284-901
284-902284-904
284-907285-601
285-605
290-681750-xxx
769-237769-176
870-501
870-507
870-531870-538
870-551
870-567
870-831870-901
880-901
AKZ 4../ AKB 4...
DLA 2.5
DLD 2.5
DLI 2.5
EK 2.5
EK 6
EK 10
EK 16
EK 35
EW15
EW35
EWK1
EWK2
IAK 1.5N 3L
IDK 1.5

MG-CPM-01 41091N 5x15

Marker

C
C
C
C
C
C
C
C
C
C

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
P

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
M C

S S C SS S C S
C
S
C S
S
C S
S
C S
S
C S
S
C S
S
C S
S
C S
S
C S
S
C S P M SC C C C M
C C C C M
C C C C M
C C C C M
C C C C M
CP CP CP CP M
C C C C M
C C C C M
C C C C M
C C C C M
C C C C M
C C C C M
C C C C M
S S S S MS
S S M

1SNC160219S0201

C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

Size mm

MG-CPM-01 41090N 5x10

4.2x9

M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M
M

MG-CPM-12 46390

5x10

P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
P
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C
C

MG-CPM-04 41390N 5x10

5x10MG-CPM-03 41293

5x7MG-CPM-02 41190N 5x10

MG-CPM-03 41291

6

Terminal block280-836
280-837
280-869
280-870
280-871
280-874
280-875
280-876
280-878
280-880
280-881280-882
280-883
280-884
280-885
280-901
280-902
280-903280-904
280-905
280-906
280-907280-912280-946281-601
281-604
281-607281-631281-652281-653281-654281-657281-659281-660281-663281-664281-666
281-668
281-678281-679
281-681281-683281-684281-685281-686281-687281-901
281-902281-903281-904
281-905281-906
281-907281-912282-601
282-604
282-607282-681282-682

MG-CPM-01 41094

Marker

MG-CPM-01 41091N 5x15

Wago
Size mm

MG-CPM-01 41090N 5x10

Wago

MG3 markers selection guidefor other manufacturers' terminal blocks

5x7

5x10

MG-CPM-01 41094

MG-CPM-02 41190N

C C C CP C C CP C C CP C C CC C C C
CP CP CP CPC C C CC C C CC C C CC C C CC C C CC C C CC C C CS S S SSS S
S S S SS S S SS S S SP C C C
S
S S
S
S S
S
S S
C
C C
S
S S
P C C CP C C CC C C C
CP CP CP CPC C C CC C C CC C C CP C C CC C C C
CP CP CP CPC C C CC C C C

5x10

5x15

5x7

5x10

MG-CPM-01 41094

MG-CPM-02 41190N

Terminal block
SAK 35
SAK 70
SAK 95SAKA 10SAKB 10SAKC 4
SAKC 10
SAKD 2.5 N
SAKG 28
SAKG 32SAKG 40SAKG 46SAKG 54SAKG 70SAKR
SAKRD
SAKS 1
SAKS 2
SAKS 3
SAKS 4
SAKS 5SAKT 1SAKT 2SAKT 4
SS 6
SS 8
SS 10
SS 12
TOP 2.5
TOP 4
VLI 2.5
WDK 2.5
WDK 2.5 800V
WDK 2.5N
WDK 4NWDL 2.5
WDL 2.5 / S
WDT 1.5
WDTR 2.5
WDU 1.5
WDU 1.5 BLA
WDU 1.5 LD/BLA
WDU 1.5/BLZ 5.08
WDU 1.5/BLZ R7.62
WDU 1.5/BLZ/LD/5.08
WDU 1.5ZZ
WDU 2.5
WDU 2.5 F
WDU 2.5 FF
WDU 2.5 N
WDU 2.5 TC
WDU 2.5/1.5/ZZ
WDU 4
WDU 4NWDU 6
WDU 10
WDU 10SL
WDU 16
WDU 35 N

MG-CPM-01 41091N

MarkerC C C CC C C CC C C CC C C CC C C CC C C CC C C CP S S SC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C C
CP CP CP CP
CP CP CP CPC C C CC C C CC C C CC C C CC C C CP C C CC C C CP C C CP S S SP C C CP S S SC C C CP C C CP C C CC C C CP C C CS S S SS S S SS S S SS S S SS S S SS S S SS S S SP S S SP S S SP S S SP S S SP S S SP S S SC C C CC C C CC C C CC C C CC C C CC C C CC C C C

6

1SNC160219S0201

5x15

Terminal block
AKZ 4../ AKB 4...
DLA 2.5
DLD 2.5
DLI 2.5
EK 2.5
EK 6
EK 10
EK 16
EK 35
EW15
EW35
EWK1
EWK2
IAK 1.5N 3L
IDK 1.5
IDK 1.5N
IDK 1.5N/V
IDU 1.5N
IDU 2.5N
IEK 1.5N
IIK 1.5N
IPE 1.5N
IPE 2.5N
ITR 1.5N
MAK 2.5
Mak 2.5/VLI 1.5
NT 4
NT 6
NT 10
NT 16
SAI-M16 / M23 in SAI-M8
SAK 2.5
SAK 4
SAK 6
SAK 10 (PA)SAK 16

5x10

Marker

MG-CPM-01 41091N

Size mm

MG-CPM-01 41090N

Weidmüller

Size mm

MG-CPM-01 41090N

M
M
M
M
M
M
M

4.2x9

S
S
S
C
S
S
S

MG-CPM-12 46390

5x10
MG-CPM-03 41293

S
S
S
C
S
S
S

MG-CPM-04 41390N 5x10

5x10MG-CPM-03 41291

S
S
S
C

5x7

S
S
S
C
S
S
S

MG-CPM-02 41190N 5x10

Terminal block
IDK 1.5N
IDK 1.5N/V
IDU 1.5N
IDU 2.5N
IEK 1.5N
IIK 1.5N
IPE 1.5N

MG-CPM-01 41094

Marker

MG-CPM-01 41091N 5x15

Weidmüller
Size mm

MG-CPM-01 41090N 5x10

Wago

PAGE 165

MG3 markers selection guidefor other manufacturers' terminal blocks

5x10

5x15

5x7

5x10

MG-CPM-01 41094

MG-CPM-02 41190N

5x10

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

Terminal block
ZDU 2.5/4AN
ZDU 2.5/4AN (/E) BL
ZDU 2.5/4AN/10
ZDU 2.5-2/3
ZDU 2.5-2/3AN (/E) BL
ZDU 2.5-2/4AN (/E)
ZDU 2.5-2/3AN (/E) BL
ZDU 2.5-2/4AN (/E)
ZDU 2.5-2/4AN (/E) BL
ZDU 2.5 (/E)
ZDU 2.5 (/E) BL
ZDU 2.5-2
ZDU 4
ZDU 6
ZDU 10 NT
ZDU 16 16/3AN
ZDU 35ZDUA 2.5-2 (/E)
ZDUA 2.5-2 (/E) BL
ZDUB 2.5 / 2-2/4AN
ZDUB 2.5 / 2AN
ZDUB 2.5-2/2AN
ZIA 1.5/....
ZK3S
ZKB
ZKS
ZPE 2.5/4AN
ZPE 2.5
ZPE 2.5/3AN
ZPE 2.5/3AN/E
ZPE 2.5/4AN
ZPE 2.5/4AN/E
ZPE 2.5/E
ZPE 2.5-2 (/E)
ZPE 2.5-2/3AN
ZPE 2.5-2/3AN/E
ZPE 2.5-2/4AN
ZPE 35ZPEA -2/E
ZRV 1.5
ZRV 1.5PE
ZSI 2.5
ZSI 2.5/2
ZSLD 2.5/1.5
ZTR 2.5
ZTR 2.5 D
ZTR 2.5/3AN
ZVL 1.5 ....

MG-CPM-01 41091N

5x7

MG-CPM-02 41190N

C C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CP S S SC C C CC C C CC C C CS S S SS S S SP S S SP C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C CC C C C
CP CP CP CP
P C C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
C
C C
C
C C
P
C C
P
C C
P C C C
P
C C
P
C C
P
C C
P
C C
P
C C
P
C C
P C C C
P
C C
P
C C
P
C C

MG-CPM-01 41090N

5x15

MG-CPM-01 41094

Marker

P C
P
P
P
P
P
C
C
P
P
P
P
C
CP
C
C
C
P
P
P
P
P
C C
C
C
C
P C
P
P
P
P
P
P
P
P C
P
P
C
C
C
C
P
P
P
P C
P C
P
C C

C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
CP CP
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C
C C

1SNC160219S0201

6

Terminal block
WDU 70/95
WDU 95N
WDU 120/150
WDU 240
WFF 35
WFF 70
WFF 120
WFF 185
WFF 300
WIN BLOCKWNT 2.5WNT 4
WNT 6
WNT 10
WPE 1.5
WPE 1.5/ZZ
WPE 2.5
WPE 2.5/1.5/ZR
WPE 4
WPE 6
WPE 10
WPE 16WPE 35
WSI 6
WSI 6/2
WTL 6/1
WTL 6/2
WTR 2.5
ZBLD 2.5/1.5
ZDK 2.5/1.5
ZDK 2.5/1.5 DU-PEZDK 2.5/1.5 N-PEZDK 2.5/1.5 V / E
ZDK 2.5/1.5/E
ZDK 2.5/1.5/E BL
ZDK 2.5/1.5/LD/1
ZDK 2.5/1.5/LD/2
ZDK 2.5/1.5/N-PE/E
ZDK 2.5/1.5D1...6
ZDK 2.5/1.5N-DU
ZDK 2.5/1.5N-DU/E
ZDK 2.5/1.5N-DU-PE/E
ZDK 2.5/1.5PE
ZDK 2.5/1.5V
ZDKB
ZDKS
ZDLD 2.5 / 1.5
ZDLD 2.5 / 1.5 V
ZDU 2.5 2.5/10
ZDU 2.5/2x2AN
ZDU 2.5/2x2AN (/E) BL
ZDU 2.5/2x2AN/10
ZDU 2.5/2x2AN/DZDU 2.5/2x2AN/E
ZDU 2.5/2x2AN/LDZDU 2.5/3AN
ZDU 2.5/3AN (/E) BL
ZDU 2.5/3AN/10
ZDU 2.5/3AN/E

5x10

MarkerSize mm

MG-CPM-01 41091N

Weidmüller
Size mm

MG-CPM-01 41090N

Weidmüller

MG3 markers selection guidefor other manufacturers' terminal blocks

5x10

5x10
STF-05 42805 bracket

P
C
C
C
C
P
C
P
C
C
C
C
C
C

M
C
C
C
C
M
C
M
C
C
C
C
C
C

M
M
M
M
M
M
M
M
M
M
M
M
M
M

MG-CPM-02 41190N 5x10

Terminal block
WT 2,5
WT 4
WT 6
WT 10
WT 16
WTP 2,5/4
WTP 6/10
WK 2,5/ U
WK 4/ UWK 6/ UWK 8/ UWK 10/ U
WK 25/ U
WK 35/ U

MG-CPM-05 41494

Marker

MG-CPM-05 41490

Size mm

3X10

Wieland

MG-CPM-01 41090N 5x1030544 / 4 V
30544 / 6 V30544 / 10 V
30800
30840
30841
30842
30843
30844

C
C
C
C
C
C
C
C
C

C C C
C C C
CP CP CP
C C C
C C C
C C C
C C C
C C C
C C C

6

1SNC160219S0201

Marker

MG-CPM-01 41094

Size mm

5x7

Terminal block

MG-CPM-01 41092

WoertzPAGE 167

HTP500 markers selection guidefor other manufacturers' terminal blocks
Terminal block
Terminal block markers are available in versions to suit the particular terminal blockformats of the most widely used products, seeselection guide to side.

Depending on type, markers are presented asjoined strips at a set or as separate markers
for convenient individual insertion on mixed
spacing terminal block assemblies.

Markers
Strip markers

Marker spacing
Marker width

Individual markers

Marker spacing
Marker width

S - Strip mounting

Marker spacing = Terminal block spacing
6

I - Individual mounting

Marker spacing ≠ Terminal block spacing

1SNC160220S0201

T - Top mounting

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONSEntrelec
M2.5/5
M4/6

I
I

Contaclip
RK 2,5RK 2,5/35
RK 2,54
RKD 2,5
RKD 2,5/35
RKD 4
RK 4...RK 240
SRK 2,5/15
SRK 2,5
IK 2,5IKD 2,5
BKA 2,5
KBL 2,5
SL 4...SL 35
TSK...
FF...
STK...
SIK...
PTK...
TRK...
ES...
EH...
ZSRK2,5...
ZRK2,5...
ZSLN 2,5
ZSL 2,5ZIKD 2,5...
ZSLD 2,5...

S
S
I
S
S
I
I
S
S
S
S
S
S
I
I
I
I
I
I
I
I
I
S
S
S
S
S
S

Klemsan
AVK 2,5
AVK 4
AVK 6
AVK 10Siemens
8WH2
8WH3
8WH4
8WH5

I
I
S
I
I
I
S
S
ST
IT
IT
S
I
I
S
I
I
I
S
I
I
I
I
S
S
I
S

Weidmüller
SAK 2,5
SAK 4
SAK 6
WDU 1,5
WDU 2,5
WDU 4
WDU 6
WDU 10
WDU 35ZDU 2,5
ZDU 6
WSI 6
WTR 2,5
WPE 2,5
WPE 4
ZPE 2,5WNT 2,5
WDK 2,5
WDK 4
Woertz
30301
30145
30150
3450
3430

RCL510 - 1SNA235097R1000 5x10

I

RCP510 - 1SNA235095R1600 5x10

StaffelTAC 10

S
I
S
I
S
I
I
I

Wago
280
281
282
283
284
290

S
I
I
I

Phoenix
ST 2,5
ST 4
ST 6
UT 2,5
UT 4
UT 6
UK 2,5
UK 3
UK 5
UK 5N
UKK 3
UKK 5
PIK 4PE/L/NL
PIK 4L/L

Terminal blockMarkerTélémécanique
AB1RR435U2
WK 4SL/UWK 4E/U
WK 4/THSI5
WK 4/UWK 6SL/U
WK 10/SIU
WKN 16/U

Legrand
10A
20A
25A
35A
50A
70A
396,2857143
390 81Rockwell Automation
1492 K3
1492 J31492 L31492 J41492 JD3C

RCL510 - 1SNA235097R1000 5x10

S
S
S
I
I
S
S
S
S
I
I

RCP510 - 1SNA235095R1600 5x10

Contaclip (cont.)
ZRKD 2,5...
ZTRK 2,5...
ZIZA 1,5...
ZRK 4...ZRK 16
ZSL 4...ZSL 16
FRK 2,5...
FSL 2,5...
FRKD 2,5...
FDLIS
FRK 4
FSL4

MarkerSize mm

I
I
I
I
I
I
I
I
I
I
S
I
I
I
I
S
I
I
S
S
I
S
S
S
I

6

S
I
I
S
S

I = individual mounting
S = strip mounting
T = top mounting

IT
IT
IT
IT

1SNC160220S0201

I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I
I

Size mm

RCW510 - 1SNA235096R1700 5x10

Arnocanali
CTS2,5UN
CTS4UNCTS6U
CTS10UCTS16U
CTS35UCSCG2,5T
CSCG4T
CSCG6T
CSCG10T
CSFL4U
CSC2,5T
CSC4T
CSC6T
CSC10T
CA702
CA802
CGT4N
CGT6N
CGT4U
CGT10U
CGT35U

Terminal block

RCW510 - 1SNA235096R1700 5x10

Terminal block

RCL510 - 1SNA235097R1000 5x10Marker

RCP510 - 1SNA235095R1600 5x10Size mm

RCW510 - 1SNA235096R1700 5x10

HTP500 markers selection guidefor other manufacturers' terminal blocks

PAGE 169

7Part Number

Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SFA616920R8120
1SNA103115R1300
1SNA103116R1400
1SNA103775R0000
1SNA103776R0100
1SNA103890R2100
1SNA103922R1400
1SNA107033R1000
1SNA107038R2500
1SNA113077R1100
1SNA113084R0100
1SNA113180R1200
1SNA163007R2600
1SNA163155R2600
1SNA163167R2200
1SNA163211R2600
1SNA163427R1700
1SNA163428R2000
1SNA163429R2100
1SNA163430R2600
1SNA163431R1300
1SNA163432R1400
1SNA163433R1500
1SNA164602R0000
1SNA164695R2500
1SNA168410R0700
1SNA168737R0200
1SNA168741R1600
1SNA168747R1400
1SNA173147R2000
1SNA173178R0700
1SNA173327R2400
1SNA173328R0500
1SNA173812R1300
1SNA178430R0500
1SNA178431R2200
1SNA206103R0700
1SNA206230R1100
1SNA206231R0600
1SNA206232R0700
1SNA206233R0000
1SNA206234R0100
1SNA206235R0200
1SNA229000R1500
1SNA229001R0200
1SNA229002R0300
1SNA229003R0400
1SNA229004R0500
1SNA229005R0600
1SNA229006R0700
1SNA229007R0000
1SNA229008R1100
1SNA229009R1200
1SNA229010R0600
1SNA229011R2300
1SNA229030R0200
1SNA229040R1400
1SNA229041R0100
1SNA229042R0200
1SNA229043R0300
1SNA229044R0400
1SNA229045R0500
1SNA229046R0600
1SNA229047R0700
1SNA229048R1000
1SNA229049R1100
1SNA229050R1600
1SNA229051R0300
1SNA229052R0400
1SNA229053R0500
1SNA229054R0600
1SNA229055R0700
1SNA229056R0000
1SNA229057R0100
1SNA229058R1200
1SNA229059R1300
1SNA229060R1000
1SNA229061R0500
1SNA229062R0600
1SNA229063R0700
1SNA229064R0000
1SNA229065R0100
1SNA229066R0200
1SNA229067R0300
1SNA229068R1400
1SNA229069R1500
1SNA229072R0000
1SNA229111R2400
1SNA229112R2500
1SNA229113R2600
1SNA229114R2700
1SNA229115R2000
1SNA229150R1700
1SNA229151R0400
1SNA229152R0500

KA1-8120
RTM7
RTM7
RC65
RC65
RC510-YL
RTM7
EPU5
EPU6
PEB
PEBM
PEV
RPEH
REH3
REH3
PEH
EP6
EP8
EP10
EP12
EP16
VSP12
VSP6
RTM9
REH3
RTM7
PETC 51
PETC 53
PETC 56
VSP16
RPEV
EP223
EP224
PIB
RCPEB
EPR1
VSP68
RC610
RC610
RC610
RC610
RC610
RC610
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

35
154
154
86
86
85
154
156
156
31
31
89
95
91
155
95
157
157
157
157
157
157
157
90
155
90
103
103
103
157
89
157
157
96
96
31
157
85
85
85
85
85
85
85
126
126
126
126
126
126
126
126
126
126
126
126
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
127
127
127
127
127
127
127
127

1SNA229153R0600
1SNA229154R0700
1SNA229155R0000
1SNA229156R0100
1SNA229157R0200
1SNA229158R1300
1SNA229159R1400
1SNA229160R1100
1SNA229161R0600
1SNA229162R0700
1SNA229163R0000
1SNA229164R0100
1SNA229165R0200
1SNA229166R0300
1SNA229167R0400
1SNA229168R1500
1SNA229169R1600
1SNA229170R1300
1SNA229171R0000
1SNA229172R0100
1SNA229173R0200
1SNA229174R0300
1SNA229175R0400
1SNA229180R0600
1SNA229181R2300
1SNA229182R2400
1SNA229183R2500
1SNA229184R2600
1SNA229185R2700
1SNA229186R2000
1SNA229187R2100
1SNA229188R0200
1SNA229189R0300
1SNA229190R0000
1SNA229191R2500
1SNA229192R2600
1SNA229193R2700
1SNA229194R2000
1SNA229195R2100
1SNA229196R2200
1SNA229197R2300
1SNA229198R0400
1SNA229199R0500
1SNA229200R2200
1SNA229201R1700
1SNA229202R1000
1SNA229203R1100
1SNA229204R1200
1SNA229205R1300
1SNA229210R1300
1SNA229211R0000
1SNA229212R0100
1SNA229213R0200
1SNA229214R0300
1SNA229215R0400
1SNA229216R0500
1SNA229217R0600
1SNA229218R1700
1SNA229220R1500
1SNA229221R0200
1SNA229222R0300
1SNA229223R0400
1SNA229224R0500
1SNA229225R0600
1SNA229226R0700
1SNA229227R0000
1SNA229228R1100
1SNA229229R1200
1SNA229230R1700
1SNA230000R1200
1SNA230001R0700
1SNA230002R0000
1SNA230003R0100
1SNA230004R0200
1SNA230005R0300
1SNA230006R0400
1SNA230007R0500
1SNA230008R1600
1SNA230009R1700
1SNA230010R0300
1SNA230011R2000
1SNA230012R2100
1SNA230013R2200
1SNA230014R2300
1SNA230015R2400
1SNA230016R2500
1SNA230017R2600
1SNA230018R0700
1SNA230019R0000
1SNA230020R0500
1SNA230021R2200
1SNA230030R0700
1SNA230031R2400
1SNA230032R2500
1SNA230033R2600

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
86
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144

1SNA230034R2700
1SNA230035R2000
1SNA230036R2100
1SNA230037R2200
1SNA230038R0300
1SNA230039R0400
1SNA230040R1100
1SNA230041R0600
1SNA230042R0700
1SNA230043R0000
1SNA230044R0100
1SNA230045R0200
1SNA230046R0300
1SNA230047R0400
1SNA230048R1500
1SNA230049R1600
1SNA230050R1300
1SNA230051R0000
1SNA230052R0100
1SNA230053R0200
1SNA230054R0300
1SNA230055R0400
1SNA230056R0500
1SNA230057R0600
1SNA230058R1700
1SNA230059R1000
1SNA230060R1500
1SNA230061R0200
1SNA230062R0300
1SNA230063R0400
1SNA230064R0500
1SNA230065R0600
1SNA230066R0700
1SNA230067R0000
1SNA230068R1100
1SNA230069R1200
1SNA230072R0500
1SNA230111R2100
1SNA230112R2200
1SNA230113R2300
1SNA230114R2400
1SNA230115R2500
1SNA230116R2600
1SNA230117R2700
1SNA230118R0000
1SNA230119R0100
1SNA230131R2500
1SNA230150R1400
1SNA230151R0100
1SNA230152R0200
1SNA230153R0300
1SNA230154R0400
1SNA230155R0500
1SNA230156R0600
1SNA230157R0700
1SNA230158R1000
1SNA230159R1100
1SNA230160R1600
1SNA230161R0300
1SNA230162R0400
1SNA230163R0500
1SNA230164R0600
1SNA230165R0700
1SNA230166R0000
1SNA230167R0100
1SNA230168R1200
1SNA230169R1300
1SNA230170R1000
1SNA230171R0500
1SNA230172R0600
1SNA230173R0700
1SNA230174R0000
1SNA230175R0100
1SNA230180R0300
1SNA230181R2000
1SNA230182R2100
1SNA230183R2200
1SNA230184R2300
1SNA230185R2400
1SNA230186R2500
1SNA230187R2600
1SNA230188R0700
1SNA230189R0000
1SNA230190R0500
1SNA230191R2200
1SNA230192R2300
1SNA230193R2400
1SNA230194R2500
1SNA230195R2600
1SNA230196R2700
1SNA230197R2000
1SNA230198R0100
1SNA230199R0200
1SNA230200R2700
1SNA230201R1400

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

144
144
144
144
144
144
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160023C0201_Index

Index
Part Number classification

IndexPart Number classification
Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNA230202R1500
1SNA230203R1600
1SNA230204R1700
1SNA230205R1000
1SNA230240R2600
1SNA230241R1300
1SNA230242R1400
1SNA230243R1500
1SNA230244R1600
1SNA230245R1700
1SNA230246R1000
1SNA230247R1100
1SNA230248R2200
1SNA230250R2000
1SNA230251R1500
1SNA230252R1600
1SNA230253R1700
1SNA230254R1000
1SNA230255R1100
1SNA230256R1200
1SNA230257R1300
1SNA230258R2400
1SNA230259R2500
1SNA230260R2200
1SNA231000R0700
1SNA231001R2400
1SNA231002R2500
1SNA231003R2600
1SNA231004R2700
1SNA231005R2000
1SNA231006R2100
1SNA231007R2200
1SNA231008R0300
1SNA231009R0400
1SNA231010R2000
1SNA231011R1500
1SNA231012R1600
1SNA231013R1700
1SNA231014R1000
1SNA231015R1100
1SNA231016R1200
1SNA231017R1300
1SNA231018R2400
1SNA231019R2500
1SNA231020R2200
1SNA231021R1700
1SNA231030R2400
1SNA231031R1100
1SNA231032R1200
1SNA231033R1300
1SNA231034R1400
1SNA231035R1500
1SNA231036R1600
1SNA231037R1700
1SNA231038R2000
1SNA231039R2100
1SNA231040R0600
1SNA231041R2300
1SNA231042R2400
1SNA231043R2500
1SNA231044R2600
1SNA231045R2700
1SNA231046R2000
1SNA231047R2100
1SNA231048R0200
1SNA231049R0300
1SNA231050R0000
1SNA231051R2500
1SNA231052R2600
1SNA231053R2700
1SNA231054R2000
1SNA231055R2100
1SNA231056R2200
1SNA231057R2300
1SNA231058R0400
1SNA231059R0500
1SNA231060R0200
1SNA231061R2700
1SNA231062R2000
1SNA231063R2100
1SNA231064R2200
1SNA231065R2300
1SNA231066R2400
1SNA231067R2500
1SNA231068R0600
1SNA231069R0700
1SNA231072R2200
1SNA231111R1600
1SNA231112R1700
1SNA231113R1000
1SNA231114R1100
1SNA231115R1200
1SNA231116R1300
1SNA231117R1400
1SNA231118R2500

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

146
146
146
146
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
85
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
131
131
131
131
131
131
131
131

1SNA231119R2600
1SNA231131R1200
1SNA231133R1400
1SNA231134R1500
1SNA231135R1600
1SNA231136R1700
1SNA231137R1000
1SNA231150R0100
1SNA231151R2600
1SNA231152R2700
1SNA231153R2000
1SNA231154R2100
1SNA231155R2200
1SNA231156R2300
1SNA231157R2400
1SNA231158R0500
1SNA231159R0600
1SNA231160R0300
1SNA231161R2000
1SNA231162R2100
1SNA231163R2200
1SNA231164R2300
1SNA231165R2400
1SNA231166R2500
1SNA231167R2600
1SNA231168R0700
1SNA231169R0000
1SNA231170R0500
1SNA231171R2200
1SNA231172R2300
1SNA231173R2400
1SNA231174R2500
1SNA231175R2600
1SNA231180R2000
1SNA231181R1500
1SNA231182R1600
1SNA231183R1700
1SNA231184R1000
1SNA231185R1100
1SNA231186R1200
1SNA231187R1300
1SNA231188R2400
1SNA231189R2500
1SNA231190R2200
1SNA231191R1700
1SNA231192R1000
1SNA231193R1100
1SNA231194R1200
1SNA231195R1300
1SNA231196R1400
1SNA231197R1500
1SNA231198R2600
1SNA231199R2700
1SNA231200R1400
1SNA231201R0100
1SNA231202R0200
1SNA231203R0300
1SNA231204R0400
1SNA231205R0500
1SNA231210R0500
1SNA231211R2200
1SNA231212R2300
1SNA231213R2400
1SNA231214R2500
1SNA231215R2600
1SNA231216R2700
1SNA231217R2000
1SNA231218R0100
1SNA231220R0700
1SNA231221R2400
1SNA231222R2500
1SNA231223R2600
1SNA231224R2700
1SNA231225R2000
1SNA231226R2100
1SNA231227R2200
1SNA231228R0300
1SNA231229R0400
1SNA231230R0100
1SNA231600R1500
1SNA231700R1100
1SNA232000R0000
1SNA232001R2500
1SNA232002R2600
1SNA232003R2700
1SNA232004R2000
1SNA232005R2100
1SNA232006R2200
1SNA232007R2300
1SNA232008R0400
1SNA232009R0500
1SNA232010R2100
1SNA232011R1600
1SNA232012R1700
1SNA232013R1000

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510TT
RC510TT-YL
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

131
131
132
132
132
132
132
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
17
17
86
147
147
147
147
147
147
147
147
147
147
147
147
147

1SNA232014R1100
1SNA232015R1200
1SNA232016R1300
1SNA232017R1400
1SNA232018R2500
1SNA232019R2600
1SNA232020R2300
1SNA232021R1000
1SNA232030R2500
1SNA232031R1200
1SNA232032R1300
1SNA232033R1400
1SNA232034R1500
1SNA232035R1600
1SNA232036R1700
1SNA232037R1000
1SNA232038R2100
1SNA232039R2200
1SNA232040R0700
1SNA232041R2400
1SNA232042R2500
1SNA232043R2600
1SNA232044R2700
1SNA232045R2000
1SNA232046R2100
1SNA232047R2200
1SNA232048R0300
1SNA232049R0400
1SNA232050R0100
1SNA232051R2600
1SNA232052R2700
1SNA232053R2000
1SNA232054R2100
1SNA232055R2200
1SNA232056R2300
1SNA232057R2400
1SNA232058R0500
1SNA232059R0600
1SNA232060R0300
1SNA232061R2000
1SNA232062R2100
1SNA232063R2200
1SNA232064R2300
1SNA232065R2400
1SNA232066R2500
1SNA232067R2600
1SNA232068R0700
1SNA232069R0000
1SNA232072R2300
1SNA232111R1700
1SNA232112R1000
1SNA232113R1100
1SNA232114R1200
1SNA232115R1300
1SNA232116R1400
1SNA232117R1500
1SNA232118R2600
1SNA232119R2700
1SNA232131R1300
1SNA232132R1400
1SNA232133R1500
1SNA232134R1600
1SNA232135R1700
1SNA232136R1000
1SNA232137R1100
1SNA232150R0200
1SNA232151R2700
1SNA232152R2000
1SNA232153R2100
1SNA232154R2200
1SNA232155R2300
1SNA232156R2400
1SNA232157R2500
1SNA232158R0600
1SNA232159R0700
1SNA232160R0400
1SNA232161R2100
1SNA232162R2200
1SNA232163R2300
1SNA232164R2400
1SNA232165R2500
1SNA232166R2600
1SNA232167R2700
1SNA232168R0000
1SNA232169R0100
1SNA232170R0600
1SNA232171R2300
1SNA232172R2400
1SNA232173R2500
1SNA232174R2600
1SNA232175R2700
1SNA232180R2100
1SNA232181R1600
1SNA232182R1700
1SNA232183R1000

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
150
150
150
150

PAGE 1717

1SNC160023C0201_Index

Part Number

7Part Number

Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNA232184R1100
1SNA232185R1200
1SNA232186R1300
1SNA232187R1400
1SNA232188R2500
1SNA232189R2600
1SNA232190R2300
1SNA232191R1000
1SNA232192R1100
1SNA232193R1200
1SNA232194R1300
1SNA232195R1400
1SNA232196R1500
1SNA232197R1600
1SNA232198R2700
1SNA232199R2000
1SNA232200R1500
1SNA232201R0200
1SNA232202R0300
1SNA232203R0400
1SNA232204R0500
1SNA232205R0600
1SNA232206R0700
1SNA232207R0000
1SNA232208R1100
1SNA232209R1200
1SNA232211R2300
1SNA232212R2400
1SNA232213R2500
1SNA232214R2600
1SNA232215R2700
1SNA232216R2000
1SNA232217R2100
1SNA232218R0200
1SNA232219R0300
1SNA232220R0000
1SNA232221R2500
1SNA232235R2300
1SNA232236R2400
1SNA232237R2500
1SNA232238R0600
1SNA232239R0700
1SNA232240R1400
1SNA232241R0100
1SNA232242R0200
1SNA232243R0300
1SNA232244R0400
1SNA232245R0500
1SNA232246R0600
1SNA232247R0700
1SNA232248R1000
1SNA232250R1600
1SNA232251R0300
1SNA232252R0400
1SNA232253R0500
1SNA232254R0600
1SNA232255R0700
1SNA232256R0000
1SNA232257R0100
1SNA232258R1200
1SNA232259R1300
1SNA232260R1000
1SNA233000R0100
1SNA233001R2600
1SNA233002R2700
1SNA233003R2000
1SNA233004R2100
1SNA233005R2200
1SNA233006R2300
1SNA233007R2400
1SNA233008R0500
1SNA233009R0600
1SNA233010R2200
1SNA233011R1700
1SNA233012R1000
1SNA233013R1100
1SNA233014R1200
1SNA233015R1300
1SNA233016R1400
1SNA233017R1500
1SNA233018R2600
1SNA233019R2700
1SNA233020R2400
1SNA233021R1100
1SNA233022R1200
1SNA233023R1300
1SNA233024R1400
1SNA233025R1500
1SNA233026R1600
1SNA233027R1700
1SNA233028R2000
1SNA233029R2100
1SNA233030R2600
1SNA233031R1300
1SNA233032R1400

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
150
150
150
150
150
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
85
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
135
135
135

1SNA233033R1500
1SNA233034R1600
1SNA233035R1700
1SNA233036R1000
1SNA233040R0000
1SNA233041R2500
1SNA233042R2600
1SNA233043R2700
1SNA233044R2000
1SNA233045R2100
1SNA233046R2200
1SNA233047R2300
1SNA233048R0400
1SNA233049R0500
1SNA233050R0200
1SNA233051R2700
1SNA233060R0400
1SNA233061R2100
1SNA233062R2200
1SNA233063R2300
1SNA233064R2400
1SNA233065R2500
1SNA233066R2600
1SNA233067R2700
1SNA233068R0000
1SNA233069R0100
1SNA233074R2600
1SNA233075R2700
1SNA233076R2000
1SNA233080R2100
1SNA233081R1600
1SNA233082R1700
1SNA233083R1000
1SNA233084R1100
1SNA233085R1200
1SNA233086R1300
1SNA233087R1400
1SNA233088R2500
1SNA233090R2300
1SNA233091R1000
1SNA233092R1100
1SNA233093R1200
1SNA233094R1300
1SNA233095R1400
1SNA233096R1500
1SNA233097R1600
1SNA233098R2700
1SNA233099R2000
1SNA233100R0200
1SNA233101R2700
1SNA233102R2000
1SNA233103R2100
1SNA233104R2200
1SNA233105R2300
1SNA233106R2400
1SNA233107R2500
1SNA233108R0600
1SNA233109R0700
1SNA233110R2300
1SNA233111R1000
1SNA233112R1100
1SNA233113R1200
1SNA233114R1300
1SNA233115R1400
1SNA233116R1500
1SNA233117R1600
1SNA233118R2700
1SNA233119R2000
1SNA233120R2500
1SNA233124R1500
1SNA233125R1600
1SNA233126R1700
1SNA233127R1000
1SNA233131R1400
1SNA233132R1500
1SNA233133R1600
1SNA233134R1700
1SNA233135R1000
1SNA233136R1100
1SNA233137R1200
1SNA233141R2600
1SNA233142R2700
1SNA233143R2000
1SNA233144R2100
1SNA233145R2200
1SNA233146R2300
1SNA233147R2400
1SNA233150R0300
1SNA233151R2000
1SNA233152R2100
1SNA233153R2200
1SNA233154R2300
1SNA233155R2400
1SNA233156R2500
1SNA233157R2600

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

135
135
135
135
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
135
135
135
137
137
137
137
137
137
137
137
137
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
136
136
136
136
136
136
136
136
136
134
138
138
138
138
136
136
135
135
135
135
135
135
135
138
138
138
138
138
136
136
136
136
136
136
136
136

1SNA233158R0700
1SNA233159R0000
1SNA233160R0500
1SNA233161R2200
1SNA233162R2300
1SNA233163R2400
1SNA233164R2500
1SNA233165R2600
1SNA233166R2700
1SNA233167R2000
1SNA233168R0100
1SNA233169R0200
1SNA233170R0700
1SNA233171R2400
1SNA233172R2500
1SNA233173R2600
1SNA233174R2700
1SNA233175R2000
1SNA233180R2200
1SNA233181R1700
1SNA233182R1000
1SNA233183R1100
1SNA233184R1200
1SNA233185R1300
1SNA233186R1400
1SNA233187R1500
1SNA233188R2600
1SNA233189R2700
1SNA233190R2400
1SNA233191R1100
1SNA233192R1200
1SNA233193R1300
1SNA233194R1400
1SNA233195R1500
1SNA233196R1600
1SNA233197R1700
1SNA233198R2000
1SNA233199R2100
1SNA233200R1600
1SNA233201R0300
1SNA233202R0400
1SNA233203R0500
1SNA233204R0600
1SNA233205R0700
1SNA233206R0000
1SNA233207R0100
1SNA233208R1200
1SNA233209R1300
1SNA233211R2400
1SNA233212R2500
1SNA233213R2600
1SNA233214R2700
1SNA233215R2000
1SNA233216R2100
1SNA233217R2200
1SNA233218R0300
1SNA233219R0400
1SNA233220R0100
1SNA233221R2600
1SNA233235R2400
1SNA233236R2500
1SNA233237R2600
1SNA233238R0700
1SNA233239R0000
1SNA233240R1500
1SNA233241R0200
1SNA233242R0300
1SNA233243R0400
1SNA233244R0500
1SNA233245R0600
1SNA233246R0700
1SNA233247R0000
1SNA233248R1100
1SNA233250R1700
1SNA233251R0400
1SNA233252R0500
1SNA233253R0600
1SNA233254R0700
1SNA233255R0000
1SNA233256R0100
1SNA233257R0200
1SNA233258R1300
1SNA233259R1400
1SNA233260R1100
1SNA233600R1700
1SNA233700R1300
1SNA234000R0200
1SNA234001R2700
1SNA234002R2000
1SNA234003R2100
1SNA234004R2200
1SNA234005R2300
1SNA234006R2400
1SNA234007R2500
1SNA234008R0600

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610TT
RC610TT-YL
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
138
138
138
138
138
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
17
17
85
139
139
139
139
139
139
139
139

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160023C0201_Index

Index
Part Number classification

IndexPart Number classification
Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNA234009R0700
1SNA234010R2300
1SNA234011R1000
1SNA234012R1100
1SNA234013R1200
1SNA234014R1300
1SNA234015R1400
1SNA234016R1500
1SNA234017R1600
1SNA234018R2700
1SNA234019R2000
1SNA234020R2500
1SNA234021R1200
1SNA234030R2700
1SNA234031R1400
1SNA234032R1500
1SNA234033R1600
1SNA234034R1700
1SNA234035R1000
1SNA234036R1100
1SNA234037R1200
1SNA234038R2300
1SNA234039R2400
1SNA234040R0100
1SNA234041R2600
1SNA234042R2700
1SNA234043R2000
1SNA234044R2100
1SNA234045R2200
1SNA234046R2300
1SNA234047R2400
1SNA234048R0500
1SNA234049R0600
1SNA234050R0300
1SNA234051R2000
1SNA234052R2100
1SNA234053R2200
1SNA234054R2300
1SNA234055R2400
1SNA234056R2500
1SNA234057R2600
1SNA234058R0700
1SNA234059R0000
1SNA234060R0500
1SNA234061R2200
1SNA234062R2300
1SNA234063R2400
1SNA234064R2500
1SNA234065R2600
1SNA234066R2700
1SNA234067R2000
1SNA234068R0100
1SNA234069R0200
1SNA234072R2500
1SNA234111R1100
1SNA234112R1200
1SNA234113R1300
1SNA234114R1400
1SNA234115R1500
1SNA234116R1600
1SNA234130R2000
1SNA234150R0400
1SNA234151R2100
1SNA234152R2200
1SNA234153R2300
1SNA234154R2400
1SNA234155R2500
1SNA234156R2600
1SNA234157R2700
1SNA234158R0000
1SNA234159R0100
1SNA234160R0600
1SNA234161R2300
1SNA234162R2400
1SNA234163R2500
1SNA234164R2600
1SNA234165R2700
1SNA234166R2000
1SNA234167R2100
1SNA234168R0200
1SNA234169R0300
1SNA234170R0000
1SNA234171R2500
1SNA234172R2600
1SNA234173R2700
1SNA234174R2000
1SNA234175R2100
1SNA234180R2300
1SNA234181R1000
1SNA234182R1100
1SNA234183R1200
1SNA234184R1300
1SNA234185R1400
1SNA234186R1500
1SNA234187R1600

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
140
140
140
140
140
140
139
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
141
141
141
141
141
141
141
141

1SNA234188R2700
1SNA234189R2000
1SNA234190R2500
1SNA234191R1200
1SNA234192R1300
1SNA234193R1400
1SNA234194R1500
1SNA234195R1600
1SNA234196R1700
1SNA234197R1000
1SNA234198R2100
1SNA234199R2200
1SNA234200R1700
1SNA234201R0400
1SNA234202R0500
1SNA234203R0600
1SNA234204R0700
1SNA234205R0000
1SNA234600R1000
1SNA234700R1400
1SNA235093R1400
1SNA235094R1500
1SNA235095R1600
1SNA235096R1700
1SNA235097R1000
1SNA235103R2300
1SNA235104R2400
1SNA235105R2500
1SNA235106R2600
1SNA235109R0100
1SNA235111R1200
1SNA235114R1500
1SNA235115R1600
1SNA235116R1700
1SNA235117R1000
1SNA235118R2100
1SNA235119R2200
1SNA235120R2700
1SNA235123R1600
1SNA235124R1700
1SNA235125R1000
1SNA235126R1100
1SNA235129R2400
1SNA235130R2100
1SNA235131R1600
1SNA235132R1700
1SNA235133R1000
1SNA235134R1100
1SNA235135R1200
1SNA235136R1300
1SNA235137R1400
1SNA235142R2100
1SNA235146R2500
1SNA235147R2600
1SNA235148R0700
1SNA235149R0000
1SNA235150R0500
1SNA235151R2200
1SNA235152R2300
1SNA235155R2600
1SNA235156R2700
1SNA235157R2000
1SNA235158R0100
1SNA235159R0200
1SNA235460R0400
1SNA235461R2100
1SNA235462R2200
1SNA235463R2300
1SNA235700R1500
1SNA235702R0300
1SNA235703R0400
1SNA235704R0500
1SNA235705R0600
1SNA235706R0700
1SNA235707R0000
1SNA235709R1200
1SNA235710R0600
1SNA235711R2300
1SNA235712R2400
1SNA235714R2600
1SNA235715R2700
1SNA235716R2000
1SNA235717R2100
1SNA235718R0200
1SNA236000R0400
1SNA236001R2100
1SNA236500R0600
1SNA236501R2300
1SNA237000R0500
1SNA237001R2200
1SNA237002R2300
1SNA237003R2400
1SNA237004R2500
1SNA237005R2600
1SNA237006R2700

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810TT
RC810TT-YL
WMTT12
WMTT18
RCP510RCW510
RCL510
PAM21515
PAM43015
PAM21520
PAM43020
PSP5015
PPB2715
PAT10060
PPT12030
PPT18050
RING122
RING124
RING127
RING1210
RING182
RING184
RING187
RING1810
SNAP152
SNAP154
SNAP157
SNAP1510
SNAP232
SNAP234
SNAP237
SNAP2310
RINGT23
RINGT209
PAM100015
PCT100015
WM12
WM18
PCGS209
RPA-TT
RPA-TT-YL
PIB2-TT
BA4
PIB2-TT-YLRCPEAD-TT
RCPEAD-TT-YL
RCCV
PIB2
PIB3
RPA
HTP500-V2 KIT
HTS500
HTP500-FEED
HTP500-PL
HTP500-PL2
HTP500-BAS
HTP500-PL3
HTP500-PW
RIB-B
RIB-R
HTP500-BA4
HTP500-CLEAN
HTP500-ROLL
HTP500-PRINT
HTP500-WB
RIB-RS
RCT610
RCT610
RCT810
RCT810
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85

141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
17
17
26
26
18
18
18
32
32
32
32
105
34
36
36
36
27
27
27
27
27
27
27
27
27
27
27
27
27
27
27
27
27
28
35
35
100
100
28
30
30
30
33
30
22
22
103
104
96
104
12
12
12
12
12
12
12
12
12
12
12
12
12
12
12
12
87
153
87
153
86
151
151
151
151
151
151

1SNA237007R2000
1SNA237008R0100
1SNA237009R0200
1SNA237010R2600
1SNA237011R1300
1SNA237012R1400
1SNA237013R1500
1SNA237014R1600
1SNA237015R1700
1SNA237016R1000
1SNA237017R1100
1SNA237018R2200
1SNA237019R2300
1SNA237020R2000
1SNA237021R1500
1SNA237030R2200
1SNA237031R1700
1SNA237032R1000
1SNA237033R1100
1SNA237034R1200
1SNA237035R1300
1SNA237036R1400
1SNA237040R0400
1SNA237041R2100
1SNA237042R2200
1SNA237043R2300
1SNA237044R2400
1SNA237045R2500
1SNA237046R2600
1SNA237047R2700
1SNA237048R0000
1SNA237049R0100
1SNA237050R0600
1SNA237051R2300
1SNA237060R0000
1SNA237061R2500
1SNA237062R2600
1SNA237063R2700
1SNA237064R2000
1SNA237065R2100
1SNA237066R2200
1SNA237067R2300
1SNA237068R0400
1SNA237074R2200
1SNA237075R2300
1SNA237076R2400
1SNA237080R2500
1SNA237081R1200
1SNA237082R1300
1SNA237083R1400
1SNA237084R1500
1SNA237085R1600
1SNA237086R1700
1SNA237087R1000
1SNA237088R2100
1SNA237131R1000
1SNA237132R1100
1SNA238000R1600
1SNA238001R0300
1SNA238002R0400
1SNA238003R0500
1SNA238004R0600
1SNA238005R0700
1SNA238006R0000
1SNA238007R0100
1SNA238008R1200
1SNA238009R1300
1SNA238010R0700
1SNA238011R2400
1SNA238012R2500
1SNA238013R2600
1SNA238014R2700
1SNA238015R2000
1SNA238016R2100
1SNA238017R2200
1SNA238018R0300
1SNA238019R0400
1SNA238020R0100
1SNA238021R2600
1SNA238022R2700
1SNA238023R2000
1SNA238024R2100
1SNA238025R2200
1SNA238026R2300
1SNA238030R0300
1SNA238031R2000
1SNA238032R2100
1SNA238033R2200
1SNA238034R2300
1SNA238035R2400
1SNA238036R2500
1SNA238037R2600
1SNA238038R0700
1SNA238039R0000
1SNA238040R1500

RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010

151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
151
151
151
152
152
152
152
152
152
152
152
152
151
151
85
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142

PAGE 1737

1SNC160023C0201_Index

Part Number

IndexPart Number classification
Type

Page

1SNA238041R0200
1SNA238050R1700
1SNA238051R0400
1SNA238052R0500
1SNA238053R0600
1SNA238054R0700
1SNA238055R0000
1SNA238056R0100
1SNA238057R0200
1SNA238058R1300
1SNA238059R1400
1SNA238060R1100
1SNA238061R0600
1SNA238062R0700
1SNA238063R0000
1SNA238064R0100
1SNA238065R0200
1SNA238066R0300
1SNA238067R0400
1SNA238068R1500
1SNA238069R1600
1SNA238070R1300
1SNA238071R0000
1SNA238072R0100
1SNA238073R0200
1SNA238074R0300
1SNA238075R0400
1SNA238080R0600
1SNA238081R2300
1SNA238082R2400
1SNA238083R2500
1SNA238084R2600
1SNA238085R2700
1SNA238086R2000
1SNA238087R2100
1SNA238088R0200
1SNA290455R0700
1SNA360000R2400
1SNA360000R2500
1SNA360010R1500
1SNA360011R0200
1SNA360011R1500
1SNA360014R0500
1SNA360015R0600
1SNA360016R0700
1SNA360017R0000
1SNA360018R1100
1SNA360019R1200
1SNA360020R1700
1SNA360021R0400
1SNA360023R0600
1SNA360024R0700
1SNA360025R0000
1SNA360026R0100
1SNA360031R0600
1SNA360036R0300
1SNA360037R0400
1SNA360038R1500
1SNA360039R1700
1SNA360040R2300
1SNA360098R1200
1SNA360100R2500
1SNA360101R1200
1SNA360103R1400
1SNA360104R1500
1SNA360105R1600
1SNA360106R1700
1SNA360120R1000
1SNA360121R0500
1SNA360122R1000
1SNA360123R0500
1SNA360124R1000
1SNA360150R2600
1SNA360155R1700
1SNA360156R1000
1SNA360161R1500
1SNA360162R1600
1SNA360163R1700
1SNA399719R1000
1SNA399725R0600
1SNA399726R0700
1SNA400252R1200
1SNB015090R4030
1SNB040090R0410
1SNB040091R0412
1SNB040092R0415
1SNB040140R0412
1SNB040141R0416
1SNB040190R0412
1SNB040191R0416
1SNB040240R0412
1SNB040241R0416
1SNB040290R0412
1SNB040291R0416
1SNB040340R0412

RC1010142
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RC1010143
RB-12W7
88
KIT MAO AMS 600
80
AMS 250 BASIC KIT80
SPRC 181
SPRCC 2103
SPRC 281
SPRC 481
SPRC 581
SPRC 681
SPRC 7
81
SPRC 881
SPRC 981
SPRC 1081
SPRC 11
81
SPRC 13
81
SPRC 1481
SPRC 15
81
SPRC 16
81
SPRC 21
81
SPRC 26
81
SPRC 27
81
SPRC 29
81
SPRC 30-3
81
SPRC 2881
PEN HOLDER
81
AMS PEN 0.25
81
AMS PEN 0.35
81
AMS PEN 0.18
81
AMS PEN 0.50
81
AMS PEN 0.70
81
AMS PEN 1.00
81
DISPOSABLE AMS PEN 0.25 81
DISPOSABLE AMS PEN 0.35 81
DISPOSABLE AMS PEN ED-R 0.25 81
DISPOSABLE AMS PEN ED-R 0.35 81
DISPOSABLE AMS PEN ED-R 0.18 81
AMS INK CARTRIDGES81
AMS CLEANER FLUID81
AMS CLEANER KIT
81
DUST COVER
12SERVICE KIT FOR AMS 600
81
SPDST1
81
PEAD
22
RCPEAD
94
EPR2
22
VSP22
157
MG-PTS 15090
67
MG-TPM 40090
60
MG-TPM 40091
60
MG-TPM 40092
60
MG-TDM-01 40140
56
MG-TDM-01 40141
56
MG-TDM-01 40190
56
MG-TDM-01 40191
56
MG-TDM-02 40240
56
MG-TDM-02 40241
56
MG-TDM-02 40290
56
MG-TDM-02 40291
56
MG2-TDMO-01 40340
57

Part Number

Type

1SNB040341R0416
1SNB040390R0412
1SNB040391R0416
1SNB040440R0412
1SNB040441R0416
1SNB040490R0412
1SNB040491R0416
1SNB040540R0412
1SNB040541R0416
1SNB040590R0412
1SNB040591R0416
1SNB041090R0510
1SNB041091R0515
1SNB041094R0507
1SNB041140R0510
1SNB041190R0510
1SNB041291R0510
1SNB041293R0510
1SNB041340R0510
1SNB041390R0510
1SNB041391R0610
1SNB041395R0510
1SNB041490R0510
1SNB041494R0510
1SNB041591R0510
1SNB041691R0510
1SNB041740R0512
1SNB041741R0612
1SNB041790R0512
1SNB041791R0612
1SNB041890R0510
1SNB042090R0410
1SNB042091R0412
1SNB042092R0415
1SNB043090R0010
1SNB043091R0076
1SNB043094R0052
1SNB043146R0012
1SNB043196R0012
1SNB044845R0915
1SNB044895R0915
1SNB044896R0920
1SNB045194R1735
1SNB045195R1744
1SNB046192R0512
1SNB046390R4209
1SNB046391R4206
1SNB046415R0615
1SNB046423R0817
1SNB046811R0052
1SNB046815R0615
1SNB046823R0817
1SNB046824R0821
1SNB046828R0715
1SNB046891R0710
1SNB046896R0920
1SNB046910R0935
1SNB046915R0615
1SNB046923R0817
1SNB046927R0512
1SNB046935R0720
1SNB046990R0010
1SNB047041R1527
1SNB047047R1827
1SNB047091R1527
1SNB047092R1549
1SNB047093R1567
1SNB047096R0827
1SNB047097R1827
1SNB047198R1543
1SNB048903R0052
1SNB049040R0920
1SNB049042R0912
1SNB049043R0915
1SNB049046R0929
1SNB049090R0920
1SNB049091R0935
1SNB049093R0915
1SNB049096R0929
1SNB049143R1527
1SNB049144R1549
1SNB049145R1567
1SNB049148R1735
1SNB049190N0920
1SNB049191R0935
1SNB049193R1527
1SNB049194R1549
1SNB049195R1567
1SNB049196R0720
1SNB049198R1735
1SNB049298R1544
1SNB049397R0915
1SNB049448R8530
1SNB049493R0817
1SNB049498R8530

MG2-TDMO-01 40341
MG2-TDMO-01 40390
MG2-TDMO-01 40391
MG2-TDMO-02 40440
MG2-TDMO-02 40441
MG2-TDMO-02 40490
MG2-TDMO-02 40491
MG2-TDMO-03 40540
MG2-TDMO-03 40541
MG2-TDMO-03 40590
MG2-TDMO-03 40591
MG-CPM-01 41090
MG-CPM-01 41091
MG-CPM-01 41094
MG-CPM-02 41140
MG-CPM-02 41190
MG-CPM-03 41291
MG-CPM-03 41293
MG-CPM-04 41340
MG-CPM-04 41390
MG-CPM-04 41391
MG-CPM-04 41395
MG-CPM-05 41490
MG-CPM-05 41494
MG-CPM-06 41591
MG-CPM-07 41691
MG-CPM-13 41740
MG-CPM-13 41741
MG-CPM-13 41790
MG-CPM-13 41791
MG-CPM-09 41890
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-CPMF 43090
MG-CPMF 43091
MG-CPMF 43094
MG-CPMFA 43146
MG-CPMFA 43196
MG-VYT 44845
MG-VYT 44895
MG-VYT 44896N
MG-TAR 45194
MG-TAR 45195
MG-CPM-10 46192
MG-CPM-12 46390
MG-CPM-12 46391
MG-VYT 46415
MG-VYT 46423
MG-VYT 46811
MG-VYT 46815
MG-VYT 46823
MG-VYT 46824
MG-VYT 46828
MG-VYT 46891
MG-VYT 46896N
MG-VYT 46910N
MG-VYT 46915
MG-VYT 46923
MG-VYT 46927
MG-VYT 46935
MG-CPMFA 46990
MG-TAP 47041N
MG-TAP 47047
MG-TAP 47091N
MG-TAP 47092N
MG-TAP 47093N
MG-TAP 47096
MG-TAP 47097
MG-TAP 47198
MG-VRT-R 48903
MG-TAPW 49040N
MG-TAPW 49042N
MG-TAPW 49043N
MG-TAPW 49046
MG-TAPW 49090N
MG-TAPW 49091N
MG-TAPW 49093N
MG-TAPW 49096
MG-TAA 49143N
MG-TAA 49144N
MG-TAA 49145N
MG-TAA 49148
MG-TAA 49190N
MG-TAA 49191N
MG-TAA 49193N
MG-TAA 49194N
MG-TAA 49195N
MG-TAA 49196
MG-TAA 49198
MG-TAA 49298
MG-TAA 49397N
MG-TAA 49448
MG-TAA 49493
MG-TAA 49498

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

Page
57
57
57
57
57
57
57
57
57
57
57
48
48
46
48
48
46
48
46
46
46
48
46
48
48
49
46
46
46
46
49
62
62
62
47
47
47
47
47
65
65
65
72
72
49
46
49
65
65
65
65
65
65
65
65
65
65
65
65
65
65
47
68
68
68
68
68
68
68
68
74
70
70
70
70
70
70
70
70
64
64
64
64
64
64
64
64
64
64
64
64
64
64
64
64

Part Number

Type

1SNB050100R0000
1SNB050102R0001
1SNB050102R0002
1SNB050110R0000
1SNB050120R0000
1SNB050122R0000
1SNB050200R0000
1SNB050202R0000
1SNB050210R0000
1SNB050212R0000
1SNB050220R0000
1SNB050222R0000
1SNB050300R0000
1SNB050302R0000
1SNB050310R0000
1SNB050312R0000
1SNB050320R0000
1SNB050322R0000
1SNB050400R0000
1SNB050402R0000
1SNB050410R0000
1SNB050411R0000
1SNB050420R0000
1SNB050421R0000
1SNB050500R0000
1SNB050510R0000
1SNB050521R0000
1SNB050600R0000
1SNB050610R0000
1SNB050620R0000
1SNB051000R0000
1SNB051010R0000
1SNB051020R0000
1SNB053010R0000
1SNB053020R0000
1SNB054142R1357
1SNB054192R1357
1SNB063020R0000
1SNB066000R0000
1SNB066010R0000
1SNB066020R0000
1SNB066040R0000
1SNB071000R0017
1SNB071001R0022
1SNB071002R0012
1SNB071040R0017
1SNB071041R0022
1SNB071042R0012
1SNB071044R0025
1SNB071050R0017
1SNB071051R0022
1SNB071052R0012
1SNB071090R0017
1SNB071091R0022
1SNB071092R0012
1SNB071094R0025
1SNB088903R0052
1SNB090000R0000
1SNB090010R0000
1SNB090020R0000
1SNB090100R0000
1SNB090110R0000
1SNB090120R0000
1SNB090200R0000
1SNB090210R0000
1SNB090220R0000
1SNB090300R0000
1SNB090310R0000
1SNB090320R0000
1SNB090400R0000
1SNB090410R0000
1SNB090420R0000
1SNB090500R0000
1SNB090510R0000
1SNB090520R0000
1SNB419001R0000
1SNB990452R0000
1SNB990453R0000
1SNB990454R0000
1SNB990455R0000
1SNB990456R0000
1SNB990513R1549
1SNB990514R1567
1SNB990653R0000
1SNB990824R0015
1SNB990826R0015
1SNB991000R0000
1SNB991002R0000
1SNB991004R0000
1SNB991005R0000
1SNB991006R0000
1SNB991007R0000
1SNB991008R0000
1SNB991010R0000
1SNB991011R0000

PM-01 50100
PM-01 50102
PM-01 50102-HF
PM-01 50110
PM-01 50120
PM-01 50122
PM-02 50200
PM-02 50202
PM-02 50210
PM-02 50212
PM-02 50220
PM-02 50222
PM-03 50300
PM-03 50302
PM-03 50310
PM-03 50312
PM-03 50320
PM-03 50322
PM-04 50400
PM-04 50402
PM-04 50410
PM-04 50411
PM-04 50420
PM-04 50421
PM-05 50500
PM-05 50510
PM-05 50521
PM-06 50600
PM-06 50610
PM-06 50620
PM-AC 51000N
PM-AC 51010N
PM-AC 51020N
PM-ET 53010
PM-ET 53020
MG-ETF 54142
MG-ETF 54192
PMF-ET 63020
PMF-AC 66000N
PMF-AC 66010N
PMF-AC 66020N
PMF-AC 66040N
MG-PLC 71000
MG-PLC 71001
MG-PLC 71002
MG-PLC 71040
MG-PLC 71041
MG-PLC 71042
MG-PLC 71044
MG-PLC 71050
MG-PLC 71051
MG-PLC 71052
MG-PLC 71090
MG-PLC 71091
MG-PLC 71092
MG-PLC 71094
MG-VRT-A 88903
PMF-00 90000
PMF-00 90010
PMF-00 90020
PMF-01 90100
PMF-01 90110
PMF-01 90120
PMF-02 90200
PMF-02 90210
PMF-02 90220
PMF-03 90300
PMF-03 90310
PMF-03 90320
PMF-04 90400
PMF-04 90410
PMF-04 90420
PMF-05 90500
PMF-05 90510
PMF-05 90520
MG3 KIT
RTR-TAP 990452
RTA-TAP 990453N
RTR-TAP 990454
RTA-TAP 990455N
RT-CCP 990456
MG-TAP-CCS 990513
MG-TAP-CCS 990514
RTA-TAPW 990653N
MG-17.5-A 990824
MG-17.5-A 990826
MG2-PWC 991000
MG2-PLT 991002
MG2-WTB 991004
MG2-STB 991005
MG2-CTB 991006
MG2-PTD 991007
MG2-MTB 991008
MG2-PTM 991010
MG2-QTB 991011

Page
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
59
59
63
63
63
63
63
73
73
73
73
73
73
73
73
73
73
73
73
73
73
74
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
43
69
69
69
69
69
71
71
70
66
66
43
43
43
43
43
43
43
43
43

1SNC160023C0201_Index

7

Part Number

IndexPart Number classification
Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNB991012R0000
1SNB991013R0000
1SNB991016R0000
1SNB991502R0000
1SNB991512R0000
1SNB991513R0000
1SNB991522R0000
1SNB991532R0000
1SNB991542R0000
1SNB991552R0000
1SNB991562R0000
1SNB991563R0000
1SNB991600R0000
1SNB991601R0000
1SNB991602R0000
1SNB991603R0000
1SNB991606R0000
1SNB991670R0000
1SNK140000R0000
1SNK140004R0000
1SNK140011R0000
1SNK140012R0000
1SNK140021R0000
1SNK140022R0000
1SNK140031R0000
1SNK140032R0000
1SNK140041R0000
1SNK140042R0000
1SNK140051R0000
1SNK140052R0000
1SNK140061R0000
1SNK140062R0000
1SNK140071R0000
1SNK140072R0000
1SNK140081R0000
1SNK140082R0000
1SNK140083R0000
1SNK140084R0000
1SNK140091R0000
1SNK140092R0000
1SNK140101R0000
1SNK140102R0000
1SNK140111R0000
1SNK140112R0000
1SNK140121R0000
1SNK140122R0000
1SNK140131R0000
1SNK140132R0000
1SNK140141R0000
1SNK140142R0000
1SNK140151R0000
1SNK140152R0000
1SNK140161R0000
1SNK140162R0000
1SNK140171R0000
1SNK140172R0000
1SNK140181R0000
1SNK140182R0000
1SNK140191R0000
1SNK140192R0000
1SNK140201R0000
1SNK140202R0000
1SNK145011R0000
1SNK145012R0000
1SNK145021R0000
1SNK145022R0000
1SNK145031R0000
1SNK145032R0000
1SNK145041R0000
1SNK145042R0000
1SNK145051R0000
1SNK145052R0000
1SNK145061R0000
1SNK145062R0000
1SNK145071R0000
1SNK145072R0000
1SNK145081R0000
1SNK145082R0000
1SNK145091R0000
1SNK145092R0000
1SNK145102R0000
1SNK146011R0000
1SNK146012R0000
1SNK146021R0000
1SNK146022R0000
1SNK146031R0000
1SNK146032R0000
1SNK146041R0000
1SNK146042R0000
1SNK146051R0000
1SNK146052R0000
1SNK146061R0000
1SNK146062R0000
1SNK146071R0000
1SNK146072R0000

MG2-ABM 991012
MG2-LTB 991013
MG2-ETB 991016
MG2-TWC 991502
MG2-TTB 991512
MG2-TMT 991513
MG2-TLT 991522
MG2-TGT 991532
MG2-TWT 991542
MG2-TST 991552
MG2-TCT 991562
MG2-TTD 991563
MG2-ETR 991600
MG2-ETR 991601
MG2-ETR 991602
MG2-ETR 991603
MG2-ETR 991606
MG2-CKP 991670
MC512
MC512-YL
MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA

43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
16
16
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
116
115
116
115
116
115
116
115
116
115
116
115
116
115
116

1SNK146081R0000
1SNK146082R0000
1SNK146091R0000
1SNK146092R0000
1SNK146101R0000
1SNK146102R0000
1SNK146111R0000
1SNK146112R0000
1SNK146121R0000
1SNK146122R0000
1SNK146131R0000
1SNK146132R0000
1SNK146141R0000
1SNK146142R0000
1SNK146151R0000
1SNK146152R0000
1SNK146161R0000
1SNK146162R0000
1SNK146171R0000
1SNK146172R0000
1SNK146181R0000
1SNK146182R0000
1SNK146191R0000
1SNK146192R0000
1SNK146201R0000
1SNK146202R0000
1SNK146211R0000
1SNK146212R0000
1SNK146221R0000
1SNK146222R0000
1SNK146231R0000
1SNK146232R0000
1SNK146241R0000
1SNK146242R0000
1SNK146251R0000
1SNK146252R0000
1SNK146261R0000
1SNK146262R0000
1SNK147001R0000
1SNK147002R0000
1SNK147011R0000
1SNK147012R0000
1SNK147021R0000
1SNK147022R0000
1SNK147031R0000
1SNK147032R0000
1SNK147041R0000
1SNK147042R0000
1SNK147051R0000
1SNK147052R0000
1SNK147061R0000
1SNK147062R0000
1SNK147071R0000
1SNK147072R0000
1SNK147081R0000
1SNK147082R0000
1SNK147091R0000
1SNK147092R0000
1SNK148001R0000
1SNK148002R0000
1SNK148011R0000
1SNK148012R0000
1SNK148021R0000
1SNK148022R0000
1SNK148031R0000
1SNK148032R0000
1SNK148041R0000
1SNK148042R0000
1SNK148051R0000
1SNK148052R0000
1SNK148061R0000
1SNK148062R0000
1SNK148071R0000
1SNK148072R0000
1SNK148091R0000
1SNK148092R0000
1SNK148101R0000
1SNK148102R0000
1SNK148111R0000
1SNK148112R0000
1SNK148121R0000
1SNK148122R0000
1SNK148131R0000
1SNK148132R0000
1SNK148141R0000
1SNK148142R0000
1SNK148151R0000
1SNK148152R0000
1SNK148161R0000
1SNK148162R0000
1SNK148171R0000
1SNK148172R0000
1SNK148181R0000
1SNK148182R0000
1SNK148192R0000

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA

115
116
115
116
115
116
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
117

1SNK148202R0000
1SNK148212R0000
1SNK148222R0000
1SNK149001R0000
1SNK149002R0000
1SNK149011R0000
1SNK149012R0000
1SNK149999R0000
1SNK150000R0000
1SNK150004R0000
1SNK150011R0000
1SNK150012R0000
1SNK150021R0000
1SNK150022R0000
1SNK150031R0000
1SNK150032R0000
1SNK150041R0000
1SNK150042R0000
1SNK150051R0000
1SNK150052R0000
1SNK150061R0000
1SNK150062R0000
1SNK150071R0000
1SNK150072R0000
1SNK150081R0000
1SNK150082R0000
1SNK150083R0000
1SNK150084R0000
1SNK150091R0000
1SNK150092R0000
1SNK150101R0000
1SNK150102R0000
1SNK150111R0000
1SNK150112R0000
1SNK150121R0000
1SNK150122R0000
1SNK150131R0000
1SNK150132R0000
1SNK150141R0000
1SNK150142R0000
1SNK150151R0000
1SNK150152R0000
1SNK150161R0000
1SNK150162R0000
1SNK150171R0000
1SNK150172R0000
1SNK150181R0000
1SNK150182R0000
1SNK150191R0000
1SNK150192R0000
1SNK150201R0000
1SNK150202R0000
1SNK155011R0000
1SNK155012R0000
1SNK155021R0000
1SNK155022R0000
1SNK155031R0000
1SNK155032R0000
1SNK155041R0000
1SNK155042R0000
1SNK155051R0000
1SNK155052R0000
1SNK155061R0000
1SNK155062R0000
1SNK155071R0000
1SNK155072R0000
1SNK155081R0000
1SNK155082R0000
1SNK155091R0000
1SNK155092R0000
1SNK155102R0000
1SNK156011R0000
1SNK156012R0000
1SNK156021R0000
1SNK156022R0000
1SNK156031R0000
1SNK156032R0000
1SNK156041R0000
1SNK156042R0000
1SNK156051R0000
1SNK156052R0000
1SNK156061R0000
1SNK156062R0000
1SNK156071R0000
1SNK156072R0000
1SNK156081R0000
1SNK156082R0000
1SNK156091R0000
1SNK156092R0000
1SNK156101R0000
1SNK156102R0000
1SNK156111R0000
1SNK156112R0000
1SNK156121R0000
1SNK156122R0000

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA
MC612
MC612-YL
MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA

117
117
117
115
117
115
117
84
16
16
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
121
119
121

PAGE 1757

1SNC160023C0201_Index

Part Number

7Part Number

Type

Page

Part Number

Type

Page

Part Number

Type

Page

1SNK156131R0000
1SNK156132R0000
1SNK156141R0000
1SNK156142R0000
1SNK156151R0000
1SNK156152R0000
1SNK156161R0000
1SNK156162R0000
1SNK156171R0000
1SNK156172R0000
1SNK156181R0000
1SNK156182R0000
1SNK156191R0000
1SNK156192R0000
1SNK156201R0000
1SNK156202R0000
1SNK156211R0000
1SNK156212R0000
1SNK156221R0000
1SNK156222R0000
1SNK156231R0000
1SNK156232R0000
1SNK156241R0000
1SNK156242R0000
1SNK156251R0000
1SNK156252R0000
1SNK156261R0000
1SNK156262R0000
1SNK157001R0000
1SNK157002R0000
1SNK157011R0000
1SNK157012R0000
1SNK157021R0000
1SNK157022R0000
1SNK157031R0000
1SNK157032R0000
1SNK157041R0000
1SNK157042R0000
1SNK157051R0000
1SNK157052R0000
1SNK157061R0000
1SNK157062R0000
1SNK157071R0000
1SNK157072R0000
1SNK157081R0000
1SNK157082R0000
1SNK157091R0000
1SNK157092R0000
1SNK158001R0000
1SNK158002R0000
1SNK158011R0000
1SNK158012R0000
1SNK158021R0000
1SNK158022R0000
1SNK158031R0000
1SNK158032R0000
1SNK158041R0000
1SNK158042R0000
1SNK158051R0000
1SNK158052R0000
1SNK158061R0000
1SNK158062R0000
1SNK158071R0000
1SNK158072R0000
1SNK158091R0000
1SNK158092R0000
1SNK158101R0000
1SNK158102R0000
1SNK158111R0000
1SNK158112R0000
1SNK158121R0000
1SNK158122R0000
1SNK158131R0000
1SNK158132R0000
1SNK158141R0000
1SNK158142R0000
1SNK158151R0000
1SNK158152R0000
1SNK158161R0000
1SNK158162R0000
1SNK158171R0000
1SNK158172R0000
1SNK158181R0000
1SNK158182R0000
1SNK158192R0000
1SNK158202R0000
1SNK158212R0000
1SNK158222R0000
1SNK159001R0000
1SNK159002R0000
1SNK159011R0000
1SNK159012R0000
1SNK159999R0000
1SNK160000R0000
1SNK160004R0000

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA
MC812
MC812-YL

119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
121
121
121
121
119
121
119
121
84
16
16

1SNK160011R0000
1SNK160012R0000
1SNK160021R0000
1SNK160022R0000
1SNK160031R0000
1SNK160032R0000
1SNK160041R0000
1SNK160042R0000
1SNK160051R0000
1SNK160052R0000
1SNK160061R0000
1SNK160062R0000
1SNK160071R0000
1SNK160072R0000
1SNK160081R0000
1SNK160082R0000
1SNK160083R0000
1SNK160084R0000
1SNK160091R0000
1SNK160092R0000
1SNK160101R0000
1SNK160102R0000
1SNK160111R0000
1SNK160112R0000
1SNK160121R0000
1SNK160122R0000
1SNK160131R0000
1SNK160132R0000
1SNK160141R0000
1SNK160142R0000
1SNK160151R0000
1SNK160152R0000
1SNK160161R0000
1SNK160162R0000
1SNK160171R0000
1SNK160172R0000
1SNK160181R0000
1SNK160182R0000
1SNK160191R0000
1SNK160192R0000
1SNK160201R0000
1SNK160202R0000
1SNK165011R0000
1SNK165012R0000
1SNK165021R0000
1SNK165022R0000
1SNK165031R0000
1SNK165032R0000
1SNK165041R0000
1SNK165042R0000
1SNK165051R0000
1SNK165052R0000
1SNK165061R0000
1SNK165062R0000
1SNK165071R0000
1SNK165072R0000
1SNK165081R0000
1SNK165082R0000
1SNK165091R0000
1SNK165092R0000
1SNK165102R0000
1SNK166011R0000
1SNK166012R0000
1SNK166021R0000
1SNK166022R0000
1SNK166031R0000
1SNK166032R0000
1SNK166041R0000
1SNK166042R0000
1SNK166051R0000
1SNK166052R0000
1SNK166061R0000
1SNK166062R0000
1SNK166071R0000
1SNK166072R0000
1SNK166081R0000
1SNK166082R0000
1SNK166091R0000
1SNK166092R0000
1SNK166101R0000
1SNK166102R0000
1SNK166111R0000
1SNK166112R0000
1SNK166121R0000
1SNK166122R0000
1SNK166131R0000
1SNK166132R0000
1SNK166141R0000
1SNK166142R0000
1SNK166151R0000
1SNK166152R0000
1SNK166161R0000
1SNK166162R0000
1SNK166171R0000
1SNK166172R0000

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA

122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
125
123
125
123
125
123
125
123
125
123
125
123
125

1SNK166181R0000
1SNK166182R0000
1SNK166191R0000
1SNK166192R0000
1SNK166201R0000
1SNK166202R0000
1SNK166211R0000
1SNK166212R0000
1SNK166221R0000
1SNK166222R0000
1SNK166231R0000
1SNK166232R0000
1SNK166241R0000
1SNK166242R0000
1SNK166251R0000
1SNK166252R0000
1SNK166261R0000
1SNK166262R0000
1SNK167001R0000
1SNK167002R0000
1SNK167011R0000
1SNK167012R0000
1SNK167021R0000
1SNK167022R0000
1SNK167031R0000
1SNK167032R0000
1SNK167041R0000
1SNK167042R0000
1SNK167051R0000
1SNK167052R0000
1SNK167061R0000
1SNK167062R0000
1SNK167071R0000
1SNK167072R0000
1SNK167081R0000
1SNK167082R0000
1SNK167091R0000
1SNK167092R0000
1SNK168001R0000
1SNK168002R0000
1SNK168011R0000
1SNK168012R0000
1SNK168021R0000
1SNK168022R0000
1SNK168031R0000
1SNK168032R0000
1SNK168041R0000
1SNK168042R0000
1SNK168051R0000
1SNK168052R0000
1SNK168061R0000
1SNK168062R0000
1SNK168071R0000
1SNK168072R0000
1SNK168091R0000
1SNK168092R0000
1SNK168101R0000
1SNK168102R0000
1SNK168111R0000
1SNK168112R0000
1SNK168121R0000
1SNK168122R0000
1SNK168131R0000
1SNK168132R0000
1SNK168141R0000
1SNK168142R0000
1SNK168151R0000
1SNK168152R0000
1SNK168161R0000
1SNK168162R0000
1SNK168171R0000
1SNK168172R0000
1SNK168181R0000
1SNK168182R0000
1SNK168192R0000
1SNK168202R0000
1SNK168212R0000
1SNK168222R0000
1SNK169001R0000
1SNK169002R0000
1SNK169011R0000
1SNK169012R0000
1SNK169999R0000
1SNK900605R0000
1SNK900607R0000
1SNK900611R0000
1SNK900630R0000
1SNK900631R0000
1SNK900633R0000
1SNK900634R0000

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA
LH
LH-R1
UMH
MCLH
MCLH-R1
MCLH-YLMCLH-R1-YL

123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
125
125
125
125
123
125
123
125
84
21
21
58
20
20
20
20

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160023C0201_Index

Index
Part Number classification

IndexType classification
Part Number

Page

Type

Part Number

Page

Type

Part NumberPage

AMS 250 BASIC KITAMS CLEANER FLUIDAMS CLEANER KITAMS INK CARTRIDGESAMS PEN 0.18
AMS PEN 0.25
AMS PEN 0.35
AMS PEN 0.50
AMS PEN 0.70
AMS PEN 1.00
BA4
DISPOSABLE AMS PEN 0.25
DISPOSABLE AMS PEN 0.35
DISPOSABLE AMS PEN ED-R 0.18
DISPOSABLE AMS PEN ED-R 0.25
DISPOSABLE AMS PEN ED-R 0.35
DUST COVER
EP10
EP12
EP16
EP223
EP224
EP6
EP8
EPR1
EPR2
EPU5
EPU6
HTP500-BA4
HTP500-BAS
HTP500-CLEAN
HTP500-FEED
HTP500-PL
HTP500-PL2
HTP500-PL3
HTP500-PRINT
HTP500-PW
HTP500-ROLL
HTP500-V2 KIT
HTP500-WB
HTS500KA1-8120
KIT MAO AMS 500
LH
LH-R1
MC512
MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA

1SNA360000R2500
1SNA360155R1700
1SNA360156R1000
1SNA360150R2600
1SNA360103R1400
1SNA360100R2500
1SNA360101R1200
1SNA360104R1500
1SNA360105R1600
1SNA360106R1700
1SNA235156R2700
1SNA360120R1000
1SNA360121R0500
1SNA360124R1000
1SNA360122R1000
1SNA360123R0500
1SNA360161R1500
1SNA163429R2100
1SNA163430R2600
1SNA163431R1300
1SNA173327R2400
1SNA173328R0500
1SNA163427R1700
1SNA163428R2000
1SNA178431R2200
1SNA399726R0700
1SNA107033R1000
1SNA107038R2500
1SNA235712R2400
1SNA235706R0700
1SNA235714R2600
1SNA235703R0400
1SNA235704R0500
1SNA235705R0600
1SNA235707R0000
1SNA235716R2000
1SNA235709R1200
1SNA235715R2700
1SNA235700R1500
1SNA235717R2100
1SNA235702R0300
1SFA616920R8120
1SNA360000R2400
1SNK900605R0000
1SNK900607R0000
1SNK140000R0000
1SNK140011R0000
1SNK140012R0000
1SNK140021R0000
1SNK140022R0000
1SNK140031R0000
1SNK140032R0000
1SNK140041R0000
1SNK140042R0000
1SNK140051R0000
1SNK140052R0000
1SNK140061R0000
1SNK140062R0000
1SNK140071R0000
1SNK140072R0000
1SNK140081R0000
1SNK140082R0000
1SNK140083R0000
1SNK140084R0000
1SNK140091R0000
1SNK140092R0000
1SNK140101R0000
1SNK140102R0000
1SNK140111R0000
1SNK140112R0000
1SNK140121R0000
1SNK140122R0000
1SNK140131R0000
1SNK140132R0000
1SNK140141R0000
1SNK140142R0000
1SNK140151R0000
1SNK140152R0000
1SNK140161R0000
1SNK140162R0000
1SNK140171R0000
1SNK140172R0000
1SNK140181R0000
1SNK140182R0000
1SNK140191R0000
1SNK140192R0000
1SNK140201R0000
1SNK140202R0000
1SNK145011R0000
1SNK145012R0000
1SNK145021R0000
1SNK145022R0000
1SNK145031R0000
1SNK145032R0000
1SNK145041R0000

80
81
81
81
81
81
81
81
81
81
33
81
81
81
81
81
12
157
157
157
157
157
157
157
31
22
156
156
12
12
12
12
12
12
12
12
12
12
12
12
12
35
80
21
21
16
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PA1SNK145042R0000
1SNK145051R0000
1SNK145052R0000
1SNK145061R0000
1SNK145062R0000
1SNK145071R0000
1SNK145072R0000
1SNK145081R0000
1SNK145082R0000
1SNK145091R0000
1SNK145092R0000
1SNK145102R0000
1SNK146011R0000
1SNK146012R0000
1SNK146021R0000
1SNK146022R0000
1SNK146031R0000
1SNK146032R0000
1SNK146041R0000
1SNK146042R0000
1SNK146051R0000
1SNK146052R0000
1SNK146061R0000
1SNK146062R0000
1SNK146071R0000
1SNK146072R0000
1SNK146081R0000
1SNK146082R0000
1SNK146091R0000
1SNK146092R0000
1SNK146101R0000
1SNK146102R0000
1SNK146111R0000
1SNK146112R0000
1SNK146121R0000
1SNK146122R0000
1SNK146131R0000
1SNK146132R0000
1SNK146141R0000
1SNK146142R0000
1SNK146151R0000
1SNK146152R0000
1SNK146161R0000
1SNK146162R0000
1SNK146171R0000
1SNK146172R0000
1SNK146181R0000
1SNK146182R0000
1SNK146191R0000
1SNK146192R0000
1SNK146201R0000
1SNK146202R0000
1SNK146211R0000
1SNK146212R0000
1SNK146221R0000
1SNK146222R0000
1SNK146231R0000
1SNK146232R0000
1SNK146241R0000
1SNK146242R0000
1SNK146251R0000
1SNK146252R0000
1SNK146261R0000
1SNK146262R0000
1SNK147001R0000
1SNK147002R0000
1SNK147011R0000
1SNK147012R0000
1SNK147021R0000
1SNK147022R0000
1SNK147031R0000
1SNK147032R0000
1SNK147041R0000
1SNK147042R0000
1SNK147051R0000
1SNK147052R0000
1SNK147061R0000
1SNK147062R0000
1SNK147071R0000
1SNK147072R0000
1SNK147081R0000
1SNK147082R0000
1SNK147091R0000
1SNK147092R0000
1SNK148001R0000
1SNK148002R0000
1SNK148011R0000
1SNK148012R0000
1SNK148021R0000
1SNK148022R0000
1SNK148031R0000
1SNK148032R0000
1SNK148041R0000
1SNK148042R0000
1SNK148051R0000

116
114
116
114
116
114
116
114
116
114
116
116
115
116
115
116
115
116
115
116
115
116
115
116
115
116
115
116
115
116
115
116
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
114
116
115
117
115
117
115
117
115
117
115
117
115

MC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512PAMC512-YL
MC612
MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK148052R0000
1SNK148061R0000
1SNK148062R0000
1SNK148071R0000
1SNK148072R0000
1SNK148091R0000
1SNK148092R0000
1SNK148101R0000
1SNK148102R0000
1SNK148111R0000
1SNK148112R0000
1SNK148121R0000
1SNK148122R0000
1SNK148131R0000
1SNK148132R0000
1SNK148141R0000
1SNK148142R0000
1SNK148151R0000
1SNK148152R0000
1SNK148161R0000
1SNK148162R0000
1SNK148171R0000
1SNK148172R0000
1SNK148181R0000
1SNK148182R0000
1SNK148192R0000
1SNK148202R0000
1SNK148212R0000
1SNK148222R0000
1SNK149001R0000
1SNK149002R0000
1SNK149011R0000
1SNK149012R0000
1SNK149999R0000
1SNK140004R0000
1SNK150000R0000
1SNK150011R0000
1SNK150012R0000
1SNK150021R0000
1SNK150022R0000
1SNK150031R0000
1SNK150032R0000
1SNK150041R0000
1SNK150042R0000
1SNK150051R0000
1SNK150052R0000
1SNK150061R0000
1SNK150062R0000
1SNK150071R0000
1SNK150072R0000
1SNK150081R0000
1SNK150082R0000
1SNK150083R0000
1SNK150084R0000
1SNK150091R0000
1SNK150092R0000
1SNK150101R0000
1SNK150102R0000
1SNK150111R0000
1SNK150112R0000
1SNK150121R0000
1SNK150122R0000
1SNK150131R0000
1SNK150132R0000
1SNK150141R0000
1SNK150142R0000
1SNK150151R0000
1SNK150152R0000
1SNK150161R0000
1SNK150162R0000
1SNK150171R0000
1SNK150172R0000
1SNK150181R0000
1SNK150182R0000
1SNK150191R0000
1SNK150192R0000
1SNK150201R0000
1SNK150202R0000
1SNK155011R0000
1SNK155012R0000
1SNK155021R0000
1SNK155022R0000
1SNK155031R0000
1SNK155032R0000
1SNK155041R0000
1SNK155042R0000
1SNK155051R0000
1SNK155052R0000
1SNK155061R0000
1SNK155062R0000
1SNK155071R0000
1SNK155072R0000
1SNK155081R0000
1SNK155082R0000
1SNK155091R0000

117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
115
117
117
117
117
117
115
117
115
117
84
16
16
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118

PAGE 177

7

1SNC160023C0201_Index

Type

7

Type

Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PA1SNK155092R0000
1SNK155102R0000
1SNK156011R0000
1SNK156012R0000
1SNK156021R0000
1SNK156022R0000
1SNK156031R0000
1SNK156032R0000
1SNK156041R0000
1SNK156042R0000
1SNK156051R0000
1SNK156052R0000
1SNK156061R0000
1SNK156062R0000
1SNK156071R0000
1SNK156072R0000
1SNK156081R0000
1SNK156082R0000
1SNK156091R0000
1SNK156092R0000
1SNK156101R0000
1SNK156102R0000
1SNK156111R0000
1SNK156112R0000
1SNK156121R0000
1SNK156122R0000
1SNK156131R0000
1SNK156132R0000
1SNK156141R0000
1SNK156142R0000
1SNK156151R0000
1SNK156152R0000
1SNK156161R0000
1SNK156162R0000
1SNK156171R0000
1SNK156172R0000
1SNK156181R0000
1SNK156182R0000
1SNK156191R0000
1SNK156192R0000
1SNK156201R0000
1SNK156202R0000
1SNK156211R0000
1SNK156212R0000
1SNK156221R0000
1SNK156222R0000
1SNK156231R0000
1SNK156232R0000
1SNK156241R0000
1SNK156242R0000
1SNK156251R0000
1SNK156252R0000
1SNK156261R0000
1SNK156262R0000
1SNK157001R0000
1SNK157002R0000
1SNK157011R0000
1SNK157012R0000
1SNK157021R0000
1SNK157022R0000
1SNK157031R0000
1SNK157032R0000
1SNK157041R0000
1SNK157042R0000
1SNK157051R0000
1SNK157052R0000
1SNK157061R0000
1SNK157062R0000
1SNK157071R0000
1SNK157072R0000
1SNK157081R0000
1SNK157082R0000
1SNK157091R0000
1SNK157092R0000
1SNK158001R0000
1SNK158002R0000
1SNK158011R0000
1SNK158012R0000
1SNK158021R0000
1SNK158022R0000
1SNK158031R0000
1SNK158032R0000
1SNK158041R0000
1SNK158042R0000
1SNK158051R0000
1SNK158052R0000
1SNK158061R0000
1SNK158062R0000
1SNK158071R0000
1SNK158072R0000
1SNK158091R0000
1SNK158092R0000
1SNK158101R0000
1SNK158102R0000
1SNK158111R0000

120
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
118
120
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
119

MC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612PAMC612-YL
MC812
MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK158112R0000
1SNK158121R0000
1SNK158122R0000
1SNK158131R0000
1SNK158132R0000
1SNK158141R0000
1SNK158142R0000
1SNK158151R0000
1SNK158152R0000
1SNK158161R0000
1SNK158162R0000
1SNK158171R0000
1SNK158172R0000
1SNK158181R0000
1SNK158182R0000
1SNK158192R0000
1SNK158202R0000
1SNK158212R0000
1SNK158222R0000
1SNK159001R0000
1SNK159002R0000
1SNK159011R0000
1SNK159012R0000
1SNK159999R0000
1SNK150004R0000
1SNK160000R0000
1SNK160011R0000
1SNK160012R0000
1SNK160021R0000
1SNK160022R0000
1SNK160031R0000
1SNK160032R0000
1SNK160041R0000
1SNK160042R0000
1SNK160051R0000
1SNK160052R0000
1SNK160061R0000
1SNK160062R0000
1SNK160071R0000
1SNK160072R0000
1SNK160081R0000
1SNK160082R0000
1SNK160083R0000
1SNK160084R0000
1SNK160091R0000
1SNK160092R0000
1SNK160101R0000
1SNK160102R0000
1SNK160111R0000
1SNK160112R0000
1SNK160121R0000
1SNK160122R0000
1SNK160131R0000
1SNK160132R0000
1SNK160141R0000
1SNK160142R0000
1SNK160151R0000
1SNK160152R0000
1SNK160161R0000
1SNK160162R0000
1SNK160171R0000
1SNK160172R0000
1SNK160181R0000
1SNK160182R0000
1SNK160191R0000
1SNK160192R0000
1SNK160201R0000
1SNK160202R0000
1SNK165011R0000
1SNK165012R0000
1SNK165021R0000
1SNK165022R0000
1SNK165031R0000
1SNK165032R0000
1SNK165041R0000
1SNK165042R0000
1SNK165051R0000
1SNK165052R0000
1SNK165061R0000
1SNK165062R0000
1SNK165071R0000
1SNK165072R0000
1SNK165081R0000
1SNK165082R0000
1SNK165091R0000
1SNK165092R0000
1SNK165102R0000
1SNK166011R0000
1SNK166012R0000
1SNK166021R0000
1SNK166022R0000
1SNK166031R0000
1SNK166032R0000
1SNK166041R0000
1SNK166042R0000

121
119
121
119
121
119
121
119
121
119
121
119
121
119
121
121
121
121
121
119
121
119
121
84
16
16
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
124
122
124
122
124
122
124
122
124

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PA1SNK166051R0000
1SNK166052R0000
1SNK166061R0000
1SNK166062R0000
1SNK166071R0000
1SNK166072R0000
1SNK166081R0000
1SNK166082R0000
1SNK166091R0000
1SNK166092R0000
1SNK166101R0000
1SNK166102R0000
1SNK166111R0000
1SNK166112R0000
1SNK166121R0000
1SNK166122R0000
1SNK166131R0000
1SNK166132R0000
1SNK166141R0000
1SNK166142R0000
1SNK166151R0000
1SNK166152R0000
1SNK166161R0000
1SNK166162R0000
1SNK166171R0000
1SNK166172R0000
1SNK166181R0000
1SNK166182R0000
1SNK166191R0000
1SNK166192R0000
1SNK166201R0000
1SNK166202R0000
1SNK166211R0000
1SNK166212R0000
1SNK166221R0000
1SNK166222R0000
1SNK166231R0000
1SNK166232R0000
1SNK166241R0000
1SNK166242R0000
1SNK166251R0000
1SNK166252R0000
1SNK166261R0000
1SNK166262R0000
1SNK167001R0000
1SNK167002R0000
1SNK167011R0000
1SNK167012R0000
1SNK167021R0000
1SNK167022R0000
1SNK167031R0000
1SNK167032R0000
1SNK167041R0000
1SNK167042R0000
1SNK167051R0000
1SNK167052R0000
1SNK167061R0000
1SNK167062R0000
1SNK167071R0000
1SNK167072R0000
1SNK167081R0000
1SNK167082R0000
1SNK167091R0000
1SNK167092R0000
1SNK168001R0000
1SNK168002R0000
1SNK168011R0000
1SNK168012R0000
1SNK168021R0000
1SNK168022R0000
1SNK168031R0000
1SNK168032R0000
1SNK168041R0000
1SNK168042R0000
1SNK168051R0000
1SNK168052R0000
1SNK168061R0000
1SNK168062R0000
1SNK168071R0000
1SNK168072R0000
1SNK168091R0000
1SNK168092R0000
1SNK168101R0000
1SNK168102R0000
1SNK168111R0000
1SNK168112R0000
1SNK168121R0000
1SNK168122R0000
1SNK168131R0000
1SNK168132R0000
1SNK168141R0000
1SNK168142R0000
1SNK168151R0000
1SNK168152R0000
1SNK168161R0000

122
124
122
124
122
124
122
124
122
124
122
124
122
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
122
124
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123
125
123

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160023C0201_Index

Index
Type classification

IndexType classification
Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

MC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812PAMC812-YL
MCLH
MCLH-R1
MCLH-R1-YL
MCLH-YL
MG-17.5-A 990824
MG-17.5-A 990826
MG2-ABM 991012
MG2-CKP 991670
MG2-CTB 991006
MG2-ETB 991016
MG2-ETR 991600
MG2-ETR 991601
MG2-ETR 991602
MG2-ETR 991603
MG2-ETR 991606
MG2-LTB 991013
MG2-MTB 991008
MG2-PLT 991002
MG2-PTD 991007
MG2-PTM 991010
MG2-PWC 991000
MG2-QTB 991011
MG2-STB 991005
MG2-TCT 991562
MG2-TDMO-01 40340
MG2-TDMO-01 40341
MG2-TDMO-01 40390
MG2-TDMO-01 40391
MG2-TDMO-02 40440
MG2-TDMO-02 40441
MG2-TDMO-02 40490
MG2-TDMO-02 40491
MG2-TDMO-03 40540
MG2-TDMO-03 40541
MG2-TDMO-03 40590
MG2-TDMO-03 40591
MG2-TGT 991532
MG2-TLT 991522
MG2-TMT 991513
MG2-TST 991552
MG2-TTB 991512
MG2-TTD 991563
MG2-TWC 991502
MG2-TWT 991542
MG2-WTB 991004
MG3 KIT
MG-CPM-01 41090
MG-CPM-01 41091
MG-CPM-01 41094
MG-CPM-02 41140
MG-CPM-02 41190
MG-CPM-03 41291
MG-CPM-03 41293
MG-CPM-04 41340
MG-CPM-04 41390
MG-CPM-04 41391
MG-CPM-04 41395
MG-CPM-05 41490
MG-CPM-05 41494
MG-CPM-06 41591
MG-CPM-07 41691
MG-CPM-09 41890
MG-CPM-10 46192
MG-CPM-12 46390
MG-CPM-12 46391
MG-CPM-13 41740
MG-CPM-13 41741
MG-CPM-13 41790
MG-CPM-13 41791
MG-CPMF 43090
MG-CPMF 43091
MG-CPMF 43094
MG-CPMFA 43146
MG-CPMFA 43196
MG-CPMFA 46990
MG-ETF 54142
MG-ETF 54192
MG-PLC 71000
MG-PLC 71001
MG-PLC 71002

1SNK168162R0000
1SNK168171R0000
1SNK168172R0000
1SNK168181R0000
1SNK168182R0000
1SNK168192R0000
1SNK168202R0000
1SNK168212R0000
1SNK168222R0000
1SNK169001R0000
1SNK169002R0000
1SNK169011R0000
1SNK169012R0000
1SNK169999R0000
1SNK160004R0000
1SNK900630R0000
1SNK900631R0000
1SNK900634R0000
1SNK900633R0000
1SNB990824R0015
1SNB990826R0015
1SNB991012R0000
1SNB991670R0000
1SNB991006R0000
1SNB991016R0000
1SNB991600R0000
1SNB991601R0000
1SNB991602R0000
1SNB991603R0000
1SNB991606R0000
1SNB991013R0000
1SNB991008R0000
1SNB991002R0000
1SNB991007R0000
1SNB991010R0000
1SNB991000R0000
1SNB991011R0000
1SNB991005R0000
1SNB991562R0000
1SNB040340R0412
1SNB040341R0416
1SNB040390R0412
1SNB040391R0416
1SNB040440R0412
1SNB040441R0416
1SNB040490R0412
1SNB040491R0416
1SNB040540R0412
1SNB040541R0416
1SNB040590R0412
1SNB040591R0416
1SNB991532R0000
1SNB991522R0000
1SNB991513R0000
1SNB991552R0000
1SNB991512R0000
1SNB991563R0000
1SNB991502R0000
1SNB991542R0000
1SNB991004R0000
1SNB419001R0000
1SNB041090R0510
1SNB041091R0515
1SNB041094R0507
1SNB041140R0510
1SNB041190R0510
1SNB041291R0510
1SNB041293R0510
1SNB041340R0510
1SNB041390R0510
1SNB041391R0610
1SNB041395R0510
1SNB041490R0510
1SNB041494R0510
1SNB041591R0510
1SNB041691R0510
1SNB041890R0510
1SNB046192R0512
1SNB046390R4209
1SNB046391R4206
1SNB041740R0512
1SNB041741R0612
1SNB041790R0512
1SNB041791R0612
1SNB043090R0010
1SNB043091R0076
1SNB043094R0052
1SNB043146R0012
1SNB043196R0012
1SNB046990R0010
1SNB054142R1357
1SNB054192R1357
1SNB071000R0017
1SNB071001R0022
1SNB071002R0012

125
123
125
123
125
125
125
125
125
123
125
123
125
84
16
20
20
20
20
66
66
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
43
57
57
57
57
57
57
57
57
57
57
57
57
43
43
43
43
43
43
43
43
43
43
48
48
46
48
48
46
48
46
46
46
48
46
48
48
49
49
49
46
49
46
46
46
46
47
47
47
47
47
47
59
59
73
73
73

MG-PLC 71040
MG-PLC 71041
MG-PLC 71042
MG-PLC 71044
MG-PLC 71050
MG-PLC 71051
MG-PLC 71052
MG-PLC 71090
MG-PLC 71091
MG-PLC 71092
MG-PLC 71094
MG-PTS 15090
MG-TAA 49143N
MG-TAA 49144N
MG-TAA 49145N
MG-TAA 49148
MG-TAA 49190N
MG-TAA 49191N
MG-TAA 49193N
MG-TAA 49194N
MG-TAA 49195N
MG-TAA 49196
MG-TAA 49198
MG-TAA 49298
MG-TAA 49397N
MG-TAA 49448
MG-TAA 49493
MG-TAA 49498
MG-TAP 47041N
MG-TAP 47047
MG-TAP 47091N
MG-TAP 47092N
MG-TAP 47093N
MG-TAP 47096
MG-TAP 47097
MG-TAP 47198
MG-TAP-CCS 990513
MG-TAP-CCS 990514
MG-TAPW 49040N
MG-TAPW 49042N
MG-TAPW 49043N
MG-TAPW 49046
MG-TAPW 49090N
MG-TAPW 49091N
MG-TAPW 49093N
MG-TAPW 49096
MG-TAR 45194
MG-TAR 45195
MG-TDM-01 40140
MG-TDM-01 40141
MG-TDM-01 40190
MG-TDM-01 40191
MG-TDM-02 40240
MG-TDM-02 40241
MG-TDM-02 40290
MG-TDM-02 40291
MG-TPM 40090
MG-TPM 40091
MG-TPM 40092
MG-TPMF 42090B
MG-TPMF 42091B
MG-TPMF 42092B
MG-VRT-A 88903
MG-VRT-R 48903
MG-VYT 44845
MG-VYT 44895
MG-VYT 44896N
MG-VYT 46415
MG-VYT 46423
MG-VYT 46811
MG-VYT 46815
MG-VYT 46823
MG-VYT 46824
MG-VYT 46828
MG-VYT 46891
MG-VYT 46896N
MG-VYT 46910N
MG-VYT 46915
MG-VYT 46923
MG-VYT 46927
MG-VYT 46935
PAM100015
PAM21515
PAM21520
PAM43015
PAM43020
PAT10060
PCGS209
PCT100015
PEAD
PEB
PEBM
PEH
PEN HOLDERPETC 51

1SNB071040R0017
1SNB071041R0022
1SNB071042R0012
1SNB071044R0025
1SNB071050R0017
1SNB071051R0022
1SNB071052R0012
1SNB071090R0017
1SNB071091R0022
1SNB071092R0012
1SNB071094R0025
1SNB015090R4030
1SNB049143R1527
1SNB049144R1549
1SNB049145R1567
1SNB049148R1735
1SNB049190N0920
1SNB049191R0935
1SNB049193R1527
1SNB049194R1549
1SNB049195R1567
1SNB049196R0720
1SNB049198R1735
1SNB049298R1544
1SNB049397R0915
1SNB049448R8530
1SNB049493R0817
1SNB049498R8530
1SNB047041R1527
1SNB047047R1827
1SNB047091R1527
1SNB047092R1549
1SNB047093R1567
1SNB047096R0827
1SNB047097R1827
1SNB047198R1543
1SNB990513R1549
1SNB990514R1567
1SNB049040R0920
1SNB049042R0912
1SNB049043R0915
1SNB049046R0929
1SNB049090R0920
1SNB049091R0935
1SNB049093R0915
1SNB049096R0929
1SNB045194R1735
1SNB045195R1744
1SNB040140R0412
1SNB040141R0416
1SNB040190R0412
1SNB040191R0416
1SNB040240R0412
1SNB040241R0416
1SNB040290R0412
1SNB040291R0416
1SNB040090R0410
1SNB040091R0412
1SNB040092R0415
1SNB042090R0410
1SNB042091R0412
1SNB042092R0415
1SNB088903R0052
1SNB048903R0052
1SNB044845R0915
1SNB044895R0915
1SNB044896R0920
1SNB046415R0615
1SNB046423R0817
1SNB046811R0052
1SNB046815R0615
1SNB046823R0817
1SNB046824R0821
1SNB046828R0715
1SNB046891R0710
1SNB046896R0920
1SNB046910R0935
1SNB046915R0615
1SNB046923R0817
1SNB046927R0512
1SNB046935R0720
1SNA235146R2500
1SNA235103R2300
1SNA235105R2500
1SNA235104R2400
1SNA235106R2600
1SNA235114R1500
1SNA235150R0500
1SNA235147R2600
1SNA399719R1000
1SNA113077R1100
1SNA113084R0100
1SNA163211R2600
1SNA360098R1200
1SNA168737R0200

73
73
73
73
73
73
73
73
73
73
73
67
64
64
64
64
64
64
64
64
64
64
64
64
64
64
64
64
68
68
68
68
68
68
68
68
71
71
70
70
70
70
70
70
70
70
72
72
56
56
56
56
56
56
56
56
60
60
60
62
62
62
74
74
65
65
65
65
65
65
65
65
65
65
65
65
65
65
65
65
65
35
32
32
32
32
36
28
35
22
31
31
95
81
103

PETC 53
PETC 56
PEV
PIB
PIB2
PIB2-TT
PIB2-TT-YL
PIB3
PM-01 50100
PM-01 50102
PM-01 50102-HF
PM-01 50110
PM-01 50120
PM-01 50122
PM-02 50200
PM-02 50202
PM-02 50210
PM-02 50212
PM-02 50220
PM-02 50222
PM-03 50300
PM-03 50302
PM-03 50310
PM-03 50312
PM-03 50320
PM-03 50322
PM-04 50400
PM-04 50402
PM-04 50410
PM-04 50411
PM-04 50420
PM-04 50421
PM-05 50500
PM-05 50510
PM-05 50521
PM-06 50600
PM-06 50610
PM-06 50620
PM-AC 51000N
PM-AC 51010N
PM-AC 51020N
PM-ET 53010
PM-ET 53020
PMF-00 90000
PMF-00 90010
PMF-00 90020
PMF-01 90100
PMF-01 90110
PMF-01 90120
PMF-02 90200
PMF-02 90210
PMF-02 90220
PMF-03 90300
PMF-03 90310
PMF-03 90320
PMF-04 90400
PMF-04 90410
PMF-04 90420
PMF-05 90500
PMF-05 90510
PMF-05 90520
PMF-AC 66000N
PMF-AC 66010N
PMF-AC 66020N
PMF-AC 66040N
PMF-ET 63020
PPB2715
PPT12030
PPT18050
PSP5015
RB-12W7
RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010

1SNA168741R1600
1SNA168747R1400
1SNA113180R1200
1SNA173812R1300
1SNA235461R2100
1SNA235155R2600
1SNA235157R2000
1SNA235462R2200
1SNB050100R0000
1SNB050102R0001
1SNB050102R0002
1SNB050110R0000
1SNB050120R0000
1SNB050122R0000
1SNB050200R0000
1SNB050202R0000
1SNB050210R0000
1SNB050212R0000
1SNB050220R0000
1SNB050222R0000
1SNB050300R0000
1SNB050302R0000
1SNB050310R0000
1SNB050312R0000
1SNB050320R0000
1SNB050322R0000
1SNB050400R0000
1SNB050402R0000
1SNB050410R0000
1SNB050411R0000
1SNB050420R0000
1SNB050421R0000
1SNB050500R0000
1SNB050510R0000
1SNB050521R0000
1SNB050600R0000
1SNB050610R0000
1SNB050620R0000
1SNB051000R0000
1SNB051010R0000
1SNB051020R0000
1SNB053010R0000
1SNB053020R0000
1SNB090000R0000
1SNB090010R0000
1SNB090020R0000
1SNB090100R0000
1SNB090110R0000
1SNB090120R0000
1SNB090200R0000
1SNB090210R0000
1SNB090220R0000
1SNB090300R0000
1SNB090310R0000
1SNB090320R0000
1SNB090400R0000
1SNB090410R0000
1SNB090420R0000
1SNB090500R0000
1SNB090510R0000
1SNB090520R0000
1SNB066000R0000
1SNB066010R0000
1SNB066020R0000
1SNB066040R0000
1SNB063020R0000
1SNA235111R1200
1SNA235115R1600
1SNA235116R1700
1SNA235109R0100
1SNA290455R0700
1SNA238000R1600
1SNA238001R0300
1SNA238002R0400
1SNA238003R0500
1SNA238004R0600
1SNA238005R0700
1SNA238006R0000
1SNA238007R0100
1SNA238008R1200
1SNA238009R1300
1SNA238010R0700
1SNA238011R2400
1SNA238012R2500
1SNA238013R2600
1SNA238014R2700
1SNA238015R2000
1SNA238016R2100
1SNA238017R2200
1SNA238018R0300
1SNA238019R0400
1SNA238020R0100
1SNA238021R2600
1SNA238022R2700
1SNA238023R2000

103
103
89
96
104
30
30
96
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
61
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
63
34
36
36
105
88
85
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
142

PAGE 1797

1SNC160023C0201_Index

Type

7

Type

Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010RC1010
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410

1SNA238024R2100
1SNA238025R2200
1SNA238026R2300
1SNA238030R0300
1SNA238031R2000
1SNA238032R2100
1SNA238033R2200
1SNA238034R2300
1SNA238035R2400
1SNA238036R2500
1SNA238037R2600
1SNA238038R0700
1SNA238039R0000
1SNA238040R1500
1SNA238041R0200
1SNA238050R1700
1SNA238051R0400
1SNA238052R0500
1SNA238053R0600
1SNA238054R0700
1SNA238055R0000
1SNA238056R0100
1SNA238057R0200
1SNA238058R1300
1SNA238059R1400
1SNA238060R1100
1SNA238061R0600
1SNA238062R0700
1SNA238063R0000
1SNA238064R0100
1SNA238065R0200
1SNA238066R0300
1SNA238067R0400
1SNA238068R1500
1SNA238069R1600
1SNA238070R1300
1SNA238071R0000
1SNA238072R0100
1SNA238073R0200
1SNA238074R0300
1SNA238075R0400
1SNA238080R0600
1SNA238081R2300
1SNA238082R2400
1SNA238083R2500
1SNA238084R2600
1SNA238085R2700
1SNA238086R2000
1SNA238087R2100
1SNA238088R0200
1SNA229000R1500
1SNA229001R0200
1SNA229002R0300
1SNA229003R0400
1SNA229004R0500
1SNA229005R0600
1SNA229006R0700
1SNA229007R0000
1SNA229008R1100
1SNA229009R1200
1SNA229010R0600
1SNA229011R2300
1SNA229030R0200
1SNA229040R1400
1SNA229041R0100
1SNA229042R0200
1SNA229043R0300
1SNA229044R0400
1SNA229045R0500
1SNA229046R0600
1SNA229047R0700
1SNA229048R1000
1SNA229049R1100
1SNA229050R1600
1SNA229051R0300
1SNA229052R0400
1SNA229053R0500
1SNA229054R0600
1SNA229055R0700
1SNA229056R0000
1SNA229057R0100
1SNA229058R1200
1SNA229059R1300
1SNA229060R1000
1SNA229061R0500
1SNA229062R0600
1SNA229063R0700
1SNA229064R0000
1SNA229065R0100
1SNA229066R0200
1SNA229067R0300
1SNA229068R1400
1SNA229069R1500
1SNA229072R0000
1SNA229111R2400

142
142
142
142
142
142
142
142
142
142
142
142
142
142
142
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
143
85
126
126
126
126
126
126
126
126
126
126
126
126
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
128
127

RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC410
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA229112R2500
1SNA229113R2600
1SNA229114R2700
1SNA229115R2000
1SNA229150R1700
1SNA229151R0400
1SNA229152R0500
1SNA229153R0600
1SNA229154R0700
1SNA229155R0000
1SNA229156R0100
1SNA229157R0200
1SNA229158R1300
1SNA229159R1400
1SNA229160R1100
1SNA229161R0600
1SNA229162R0700
1SNA229163R0000
1SNA229164R0100
1SNA229165R0200
1SNA229166R0300
1SNA229167R0400
1SNA229168R1500
1SNA229169R1600
1SNA229170R1300
1SNA229171R0000
1SNA229172R0100
1SNA229173R0200
1SNA229174R0300
1SNA229175R0400
1SNA229180R0600
1SNA229181R2300
1SNA229182R2400
1SNA229183R2500
1SNA229184R2600
1SNA229185R2700
1SNA229186R2000
1SNA229187R2100
1SNA229188R0200
1SNA229189R0300
1SNA229190R0000
1SNA229191R2500
1SNA229192R2600
1SNA229193R2700
1SNA229194R2000
1SNA229195R2100
1SNA229196R2200
1SNA229197R2300
1SNA229198R0400
1SNA229199R0500
1SNA229200R2200
1SNA229201R1700
1SNA229202R1000
1SNA229203R1100
1SNA229204R1200
1SNA229205R1300
1SNA229210R1300
1SNA229211R0000
1SNA229212R0100
1SNA229213R0200
1SNA229214R0300
1SNA229215R0400
1SNA229216R0500
1SNA229217R0600
1SNA229218R1700
1SNA229220R1500
1SNA229221R0200
1SNA229222R0300
1SNA229223R0400
1SNA229224R0500
1SNA229225R0600
1SNA229226R0700
1SNA229227R0000
1SNA229228R1100
1SNA229229R1200
1SNA229230R1700
1SNA231000R0700
1SNA231001R2400
1SNA231002R2500
1SNA231003R2600
1SNA231004R2700
1SNA231005R2000
1SNA231006R2100
1SNA231007R2200
1SNA231008R0300
1SNA231009R0400
1SNA231010R2000
1SNA231011R1500
1SNA231012R1600
1SNA231013R1700
1SNA231014R1000
1SNA231015R1100
1SNA231016R1200
1SNA231017R1300
1SNA231018R2400

127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
127
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
129
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
126
85
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510

1SNA231019R2500
1SNA231020R2200
1SNA231021R1700
1SNA231030R2400
1SNA231031R1100
1SNA231032R1200
1SNA231033R1300
1SNA231034R1400
1SNA231035R1500
1SNA231036R1600
1SNA231037R1700
1SNA231038R2000
1SNA231039R2100
1SNA231040R0600
1SNA231041R2300
1SNA231042R2400
1SNA231043R2500
1SNA231044R2600
1SNA231045R2700
1SNA231046R2000
1SNA231047R2100
1SNA231048R0200
1SNA231049R0300
1SNA231050R0000
1SNA231051R2500
1SNA231052R2600
1SNA231053R2700
1SNA231054R2000
1SNA231055R2100
1SNA231056R2200
1SNA231057R2300
1SNA231058R0400
1SNA231059R0500
1SNA231060R0200
1SNA231061R2700
1SNA231062R2000
1SNA231063R2100
1SNA231064R2200
1SNA231065R2300
1SNA231066R2400
1SNA231067R2500
1SNA231068R0600
1SNA231069R0700
1SNA231072R2200
1SNA231111R1600
1SNA231112R1700
1SNA231113R1000
1SNA231114R1100
1SNA231115R1200
1SNA231116R1300
1SNA231117R1400
1SNA231118R2500
1SNA231119R2600
1SNA231131R1200
1SNA231133R1400
1SNA231134R1500
1SNA231135R1600
1SNA231136R1700
1SNA231137R1000
1SNA231150R0100
1SNA231151R2600
1SNA231152R2700
1SNA231153R2000
1SNA231154R2100
1SNA231155R2200
1SNA231156R2300
1SNA231157R2400
1SNA231158R0500
1SNA231159R0600
1SNA231160R0300
1SNA231161R2000
1SNA231162R2100
1SNA231163R2200
1SNA231164R2300
1SNA231165R2400
1SNA231166R2500
1SNA231167R2600
1SNA231168R0700
1SNA231169R0000
1SNA231170R0500
1SNA231171R2200
1SNA231172R2300
1SNA231173R2400
1SNA231174R2500
1SNA231175R2600
1SNA231180R2000
1SNA231181R1500
1SNA231182R1600
1SNA231183R1700
1SNA231184R1000
1SNA231185R1100
1SNA231186R1200
1SNA231187R1300
1SNA231188R2400
1SNA231189R2500

130
130
130
130
130
130
130
130
130
130
130
130
130
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
132
131
131
131
131
131
131
131
131
131
131
132
132
132
132
132
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
131
133
133
133
133
133
133
133
133
133
133

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160023C0201_Index

Index
Type classification

IndexType classification
Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510
RC510TT
RC510TT-YL
RC510-YL
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55

1SNA231190R2200
1SNA231191R1700
1SNA231192R1000
1SNA231193R1100
1SNA231194R1200
1SNA231195R1300
1SNA231196R1400
1SNA231197R1500
1SNA231198R2600
1SNA231199R2700
1SNA231200R1400
1SNA231201R0100
1SNA231202R0200
1SNA231203R0300
1SNA231204R0400
1SNA231205R0500
1SNA231210R0500
1SNA231211R2200
1SNA231212R2300
1SNA231213R2400
1SNA231214R2500
1SNA231215R2600
1SNA231216R2700
1SNA231217R2000
1SNA231218R0100
1SNA231220R0700
1SNA231221R2400
1SNA231222R2500
1SNA231223R2600
1SNA231224R2700
1SNA231225R2000
1SNA231226R2100
1SNA231227R2200
1SNA231228R0300
1SNA231229R0400
1SNA231230R0100
1SNA231600R1500
1SNA231700R1100
1SNA103890R2100
1SNA230000R1200
1SNA230001R0700
1SNA230002R0000
1SNA230003R0100
1SNA230004R0200
1SNA230005R0300
1SNA230006R0400
1SNA230007R0500
1SNA230008R1600
1SNA230009R1700
1SNA230010R0300
1SNA230011R2000
1SNA230012R2100
1SNA230013R2200
1SNA230014R2300
1SNA230015R2400
1SNA230016R2500
1SNA230017R2600
1SNA230018R0700
1SNA230019R0000
1SNA230020R0500
1SNA230021R2200
1SNA230030R0700
1SNA230031R2400
1SNA230032R2500
1SNA230033R2600
1SNA230034R2700
1SNA230035R2000
1SNA230036R2100
1SNA230037R2200
1SNA230038R0300
1SNA230039R0400
1SNA230040R1100
1SNA230041R0600
1SNA230042R0700
1SNA230043R0000
1SNA230044R0100
1SNA230045R0200
1SNA230046R0300
1SNA230047R0400
1SNA230048R1500
1SNA230049R1600
1SNA230050R1300
1SNA230051R0000
1SNA230052R0100
1SNA230053R0200
1SNA230054R0300
1SNA230055R0400
1SNA230056R0500
1SNA230057R0600
1SNA230058R1700
1SNA230059R1000
1SNA230060R1500
1SNA230061R0200
1SNA230062R0300
1SNA230063R0400

133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
133
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
130
17
17
85
86
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146

RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC55
RC610
RC610
RC610
RC610
RC610
RC610

1SNA230064R0500
1SNA230065R0600
1SNA230066R0700
1SNA230067R0000
1SNA230068R1100
1SNA230069R1200
1SNA230072R0500
1SNA230111R2100
1SNA230112R2200
1SNA230113R2300
1SNA230114R2400
1SNA230115R2500
1SNA230116R2600
1SNA230117R2700
1SNA230118R0000
1SNA230119R0100
1SNA230131R2500
1SNA230150R1400
1SNA230151R0100
1SNA230152R0200
1SNA230153R0300
1SNA230154R0400
1SNA230155R0500
1SNA230156R0600
1SNA230157R0700
1SNA230158R1000
1SNA230159R1100
1SNA230160R1600
1SNA230161R0300
1SNA230162R0400
1SNA230163R0500
1SNA230164R0600
1SNA230165R0700
1SNA230166R0000
1SNA230167R0100
1SNA230168R1200
1SNA230169R1300
1SNA230170R1000
1SNA230171R0500
1SNA230172R0600
1SNA230173R0700
1SNA230174R0000
1SNA230175R0100
1SNA230180R0300
1SNA230181R2000
1SNA230182R2100
1SNA230183R2200
1SNA230184R2300
1SNA230185R2400
1SNA230186R2500
1SNA230187R2600
1SNA230188R0700
1SNA230189R0000
1SNA230190R0500
1SNA230191R2200
1SNA230192R2300
1SNA230193R2400
1SNA230194R2500
1SNA230195R2600
1SNA230196R2700
1SNA230197R2000
1SNA230198R0100
1SNA230199R0200
1SNA230200R2700
1SNA230201R1400
1SNA230202R1500
1SNA230203R1600
1SNA230204R1700
1SNA230205R1000
1SNA230240R2600
1SNA230241R1300
1SNA230242R1400
1SNA230243R1500
1SNA230244R1600
1SNA230245R1700
1SNA230246R1000
1SNA230247R1100
1SNA230248R2200
1SNA230250R2000
1SNA230251R1500
1SNA230252R1600
1SNA230253R1700
1SNA230254R1000
1SNA230255R1100
1SNA230256R1200
1SNA230257R1300
1SNA230258R2400
1SNA230259R2500
1SNA230260R2200
1SNA206230R1100
1SNA206231R0600
1SNA206232R0700
1SNA206233R0000
1SNA206234R0100
1SNA206235R0200

146
146
146
146
146
146
146
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
145
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
146
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
144
85
85
85
85
85
85

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233000R0100
1SNA233001R2600
1SNA233002R2700
1SNA233003R2000
1SNA233004R2100
1SNA233005R2200
1SNA233006R2300
1SNA233007R2400
1SNA233008R0500
1SNA233009R0600
1SNA233010R2200
1SNA233011R1700
1SNA233012R1000
1SNA233013R1100
1SNA233014R1200
1SNA233015R1300
1SNA233016R1400
1SNA233017R1500
1SNA233018R2600
1SNA233019R2700
1SNA233020R2400
1SNA233021R1100
1SNA233022R1200
1SNA233023R1300
1SNA233024R1400
1SNA233025R1500
1SNA233026R1600
1SNA233027R1700
1SNA233028R2000
1SNA233029R2100
1SNA233030R2600
1SNA233031R1300
1SNA233032R1400
1SNA233033R1500
1SNA233034R1600
1SNA233035R1700
1SNA233036R1000
1SNA233040R0000
1SNA233041R2500
1SNA233042R2600
1SNA233043R2700
1SNA233044R2000
1SNA233045R2100
1SNA233046R2200
1SNA233047R2300
1SNA233048R0400
1SNA233049R0500
1SNA233050R0200
1SNA233051R2700
1SNA233060R0400
1SNA233061R2100
1SNA233062R2200
1SNA233063R2300
1SNA233064R2400
1SNA233065R2500
1SNA233066R2600
1SNA233067R2700
1SNA233068R0000
1SNA233069R0100
1SNA233074R2600
1SNA233075R2700
1SNA233076R2000
1SNA233080R2100
1SNA233081R1600
1SNA233082R1700
1SNA233083R1000
1SNA233084R1100
1SNA233085R1200
1SNA233086R1300
1SNA233087R1400
1SNA233088R2500
1SNA233090R2300
1SNA233091R1000
1SNA233092R1100
1SNA233093R1200
1SNA233094R1300
1SNA233095R1400
1SNA233096R1500
1SNA233097R1600
1SNA233098R2700
1SNA233099R2000
1SNA233100R0200
1SNA233101R2700
1SNA233102R2000
1SNA233103R2100
1SNA233104R2200
1SNA233105R2300
1SNA233106R2400
1SNA233107R2500
1SNA233108R0600
1SNA233109R0700
1SNA233110R2300
1SNA233111R1000
1SNA233112R1100
1SNA233113R1200

85
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
135
135
135
135
135
135
135
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
135
135
135
137
137
137
137
137
137
137
137
137
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
134
136
136
136

PAGE 1817

1SNC160023C0201_Index

Type

7

Type

Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610

1SNA233114R1300
1SNA233115R1400
1SNA233116R1500
1SNA233117R1600
1SNA233118R2700
1SNA233119R2000
1SNA233120R2500
1SNA233124R1500
1SNA233125R1600
1SNA233126R1700
1SNA233127R1000
1SNA233131R1400
1SNA233132R1500
1SNA233133R1600
1SNA233134R1700
1SNA233135R1000
1SNA233136R1100
1SNA233137R1200
1SNA233141R2600
1SNA233142R2700
1SNA233143R2000
1SNA233144R2100
1SNA233145R2200
1SNA233146R2300
1SNA233147R2400
1SNA233150R0300
1SNA233151R2000
1SNA233152R2100
1SNA233153R2200
1SNA233154R2300
1SNA233155R2400
1SNA233156R2500
1SNA233157R2600
1SNA233158R0700
1SNA233159R0000
1SNA233160R0500
1SNA233161R2200
1SNA233162R2300
1SNA233163R2400
1SNA233164R2500
1SNA233165R2600
1SNA233166R2700
1SNA233167R2000
1SNA233168R0100
1SNA233169R0200
1SNA233170R0700
1SNA233171R2400
1SNA233172R2500
1SNA233173R2600
1SNA233174R2700
1SNA233175R2000
1SNA233180R2200
1SNA233181R1700
1SNA233182R1000
1SNA233183R1100
1SNA233184R1200
1SNA233185R1300
1SNA233186R1400
1SNA233187R1500
1SNA233188R2600
1SNA233189R2700
1SNA233190R2400
1SNA233191R1100
1SNA233192R1200
1SNA233193R1300
1SNA233194R1400
1SNA233195R1500
1SNA233196R1600
1SNA233197R1700
1SNA233198R2000
1SNA233199R2100
1SNA233200R1600
1SNA233201R0300
1SNA233202R0400
1SNA233203R0500
1SNA233204R0600
1SNA233205R0700
1SNA233206R0000
1SNA233207R0100
1SNA233208R1200
1SNA233209R1300
1SNA233211R2400
1SNA233212R2500
1SNA233213R2600
1SNA233214R2700
1SNA233215R2000
1SNA233216R2100
1SNA233217R2200
1SNA233218R0300
1SNA233219R0400
1SNA233220R0100
1SNA233221R2600
1SNA233235R2400
1SNA233236R2500
1SNA233237R2600

136
136
136
136
136
136
134
138
138
138
138
136
136
135
135
135
135
135
135
135
138
138
138
138
138
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
136
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
138
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
135
138
138
138

RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610
RC610TT
RC610TT-YL
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA233238R0700
1SNA233239R0000
1SNA233240R1500
1SNA233241R0200
1SNA233242R0300
1SNA233243R0400
1SNA233244R0500
1SNA233245R0600
1SNA233246R0700
1SNA233247R0000
1SNA233248R1100
1SNA233250R1700
1SNA233251R0400
1SNA233252R0500
1SNA233253R0600
1SNA233254R0700
1SNA233255R0000
1SNA233256R0100
1SNA233257R0200
1SNA233258R1300
1SNA233259R1400
1SNA233260R1100
1SNA233600R1700
1SNA233700R1300
1SNA103775R0000
1SNA103776R0100
1SNA232000R0000
1SNA232001R2500
1SNA232002R2600
1SNA232003R2700
1SNA232004R2000
1SNA232005R2100
1SNA232006R2200
1SNA232007R2300
1SNA232008R0400
1SNA232009R0500
1SNA232010R2100
1SNA232011R1600
1SNA232012R1700
1SNA232013R1000
1SNA232014R1100
1SNA232015R1200
1SNA232016R1300
1SNA232017R1400
1SNA232018R2500
1SNA232019R2600
1SNA232020R2300
1SNA232021R1000
1SNA232030R2500
1SNA232031R1200
1SNA232032R1300
1SNA232033R1400
1SNA232034R1500
1SNA232035R1600
1SNA232036R1700
1SNA232037R1000
1SNA232038R2100
1SNA232039R2200
1SNA232040R0700
1SNA232041R2400
1SNA232042R2500
1SNA232043R2600
1SNA232044R2700
1SNA232045R2000
1SNA232046R2100
1SNA232047R2200
1SNA232048R0300
1SNA232049R0400
1SNA232050R0100
1SNA232051R2600
1SNA232052R2700
1SNA232053R2000
1SNA232054R2100
1SNA232055R2200
1SNA232056R2300
1SNA232057R2400
1SNA232058R0500
1SNA232059R0600
1SNA232060R0300
1SNA232061R2000
1SNA232062R2100
1SNA232063R2200
1SNA232064R2300
1SNA232065R2400
1SNA232066R2500
1SNA232067R2600
1SNA232068R0700
1SNA232069R0000
1SNA232072R2300
1SNA232111R1700
1SNA232112R1000
1SNA232113R1100
1SNA232114R1200
1SNA232115R1300
1SNA232116R1400

138
138
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
137
17
17
86
86
86
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
149
148
148
148
148
148
148

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC65

1SNA232117R1500
1SNA232118R2600
1SNA232119R2700
1SNA232131R1300
1SNA232132R1400
1SNA232133R1500
1SNA232134R1600
1SNA232135R1700
1SNA232136R1000
1SNA232137R1100
1SNA232150R0200
1SNA232151R2700
1SNA232152R2000
1SNA232153R2100
1SNA232154R2200
1SNA232155R2300
1SNA232156R2400
1SNA232157R2500
1SNA232158R0600
1SNA232159R0700
1SNA232160R0400
1SNA232161R2100
1SNA232162R2200
1SNA232163R2300
1SNA232164R2400
1SNA232165R2500
1SNA232166R2600
1SNA232167R2700
1SNA232168R0000
1SNA232169R0100
1SNA232170R0600
1SNA232171R2300
1SNA232172R2400
1SNA232173R2500
1SNA232174R2600
1SNA232175R2700
1SNA232180R2100
1SNA232181R1600
1SNA232182R1700
1SNA232183R1000
1SNA232184R1100
1SNA232185R1200
1SNA232186R1300
1SNA232187R1400
1SNA232188R2500
1SNA232189R2600
1SNA232190R2300
1SNA232191R1000
1SNA232192R1100
1SNA232193R1200
1SNA232194R1300
1SNA232195R1400
1SNA232196R1500
1SNA232197R1600
1SNA232198R2700
1SNA232199R2000
1SNA232200R1500
1SNA232201R0200
1SNA232202R0300
1SNA232203R0400
1SNA232204R0500
1SNA232205R0600
1SNA232206R0700
1SNA232207R0000
1SNA232208R1100
1SNA232209R1200
1SNA232211R2300
1SNA232212R2400
1SNA232213R2500
1SNA232214R2600
1SNA232215R2700
1SNA232216R2000
1SNA232217R2100
1SNA232218R0200
1SNA232219R0300
1SNA232220R0000
1SNA232221R2500
1SNA232235R2300
1SNA232236R2400
1SNA232237R2500
1SNA232238R0600
1SNA232239R0700
1SNA232240R1400
1SNA232241R0100
1SNA232242R0200
1SNA232243R0300
1SNA232244R0400
1SNA232245R0500
1SNA232246R0600
1SNA232247R0700
1SNA232248R1000
1SNA232250R1600
1SNA232251R0300
1SNA232252R0400
1SNA232253R0500

148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
148
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
150
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
147
150
150
150
150
150
149
149
149
149
149
149
149
149
149
149
149
149
149

INDUSTRIAL /// ENTRELEC TERMINAL BLOCKS - MARKING SOLUTIONS

1SNC160023C0201_Index

Index
Type classification

IndexType classification
Part Number

Page

Type

Part Number

Page

Type

Part Number

Page

RC65
RC65
RC65
RC65
RC65
RC65
RC65
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810

1SNA232254R0600
1SNA232255R0700
1SNA232256R0000
1SNA232257R0100
1SNA232258R1200
1SNA232259R1300
1SNA232260R1000
1SNA234000R0200
1SNA234001R2700
1SNA234002R2000
1SNA234003R2100
1SNA234004R2200
1SNA234005R2300
1SNA234006R2400
1SNA234007R2500
1SNA234008R0600
1SNA234009R0700
1SNA234010R2300
1SNA234011R1000
1SNA234012R1100
1SNA234013R1200
1SNA234014R1300
1SNA234015R1400
1SNA234016R1500
1SNA234017R1600
1SNA234018R2700
1SNA234019R2000
1SNA234020R2500
1SNA234021R1200
1SNA234030R2700
1SNA234031R1400
1SNA234032R1500
1SNA234033R1600
1SNA234034R1700
1SNA234035R1000
1SNA234036R1100
1SNA234037R1200
1SNA234038R2300
1SNA234039R2400
1SNA234040R0100
1SNA234041R2600
1SNA234042R2700
1SNA234043R2000
1SNA234044R2100
1SNA234045R2200
1SNA234046R2300
1SNA234047R2400
1SNA234048R0500
1SNA234049R0600
1SNA234050R0300
1SNA234051R2000
1SNA234052R2100
1SNA234053R2200
1SNA234054R2300
1SNA234055R2400
1SNA234056R2500
1SNA234057R2600
1SNA234058R0700
1SNA234059R0000
1SNA234060R0500
1SNA234061R2200
1SNA234062R2300
1SNA234063R2400
1SNA234064R2500
1SNA234065R2600
1SNA234066R2700
1SNA234067R2000
1SNA234068R0100
1SNA234069R0200
1SNA234072R2500
1SNA234111R1100
1SNA234112R1200
1SNA234113R1300
1SNA234114R1400
1SNA234115R1500
1SNA234116R1600
1SNA234130R2000
1SNA234150R0400
1SNA234151R2100
1SNA234152R2200
1SNA234153R2300
1SNA234154R2400
1SNA234155R2500
1SNA234156R2600
1SNA234157R2700
1SNA234158R0000
1SNA234159R0100
1SNA234160R0600
1SNA234161R2300
1SNA234162R2400
1SNA234163R2500
1SNA234164R2600
1SNA234165R2700
1SNA234166R2000
1SNA234167R2100

149
149
149
149
149
149
149
85
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
139
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
140
140
140
140
140
140
139
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140
140

RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810
RC810TT
RC810TT-YL
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85
RCAL85

1SNA234168R0200
1SNA234169R0300
1SNA234170R0000
1SNA234171R2500
1SNA234172R2600
1SNA234173R2700
1SNA234174R2000
1SNA234175R2100
1SNA234180R2300
1SNA234181R1000
1SNA234182R1100
1SNA234183R1200
1SNA234184R1300
1SNA234185R1400
1SNA234186R1500
1SNA234187R1600
1SNA234188R2700
1SNA234189R2000
1SNA234190R2500
1SNA234191R1200
1SNA234192R1300
1SNA234193R1400
1SNA234194R1500
1SNA234195R1600
1SNA234196R1700
1SNA234197R1000
1SNA234198R2100
1SNA234199R2200
1SNA234200R1700
1SNA234201R0400
1SNA234202R0500
1SNA234203R0600
1SNA234204R0700
1SNA234205R0000
1SNA234600R1000
1SNA234700R1400
1SNA237000R0500
1SNA237001R2200
1SNA237002R2300
1SNA237003R2400
1SNA237004R2500
1SNA237005R2600
1SNA237006R2700
1SNA237007R2000
1SNA237008R0100
1SNA237009R0200
1SNA237010R2600
1SNA237011R1300
1SNA237012R1400
1SNA237013R1500
1SNA237014R1600
1SNA237015R1700
1SNA237016R1000
1SNA237017R1100
1SNA237018R2200
1SNA237019R2300
1SNA237020R2000
1SNA237021R1500
1SNA237030R2200
1SNA237031R1700
1SNA237032R1000
1SNA237033R1100
1SNA237034R1200
1SNA237035R1300
1SNA237036R1400
1SNA237040R0400
1SNA237041R2100
1SNA237042R2200
1SNA237043R2300
1SNA237044R2400
1SNA237045R2500
1SNA237046R2600
1SNA237047R2700
1SNA237048R0000
1SNA237049R0100
1SNA237050R0600
1SNA237051R2300
1SNA237060R0000
1SNA237061R2500
1SNA237062R2600
1SNA237063R2700
1SNA237064R2000
1SNA237065R2100
1SNA237066R2200
1SNA237067R2300
1SNA237068R0400
1SNA237074R2200
1SNA237075R2300
1SNA237076R2400
1SNA237080R2500
1SNA237081R1200
1SNA237082R1300
1SNA237083R1400
1SNA237084R1500
1SNA237085R1600

140
140
140
140
140
140
140
140
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
141
17
17
86
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
151
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
152
151
151
151
152
152
152
152
152
152

RCAL85
RCAL85
RCAL85
RCAL85
RCAL85RCCV
RCL510
RCP510RCPEAD
RCPEAD-TT
RCPEAD-TT-YL
RCPEB
RCT610
RCT610
RCT810
RCT810RCW510
REH3
REH3
REH3
RIB-B
RIB-R
RIB-RS
RING1210
RING122
RING124
RING127
RING1810
RING182
RING184
RING187
RINGT209
RINGT23RPA
RPA-TT
RPA-TT-YL
RPEH
RPEV
RTA-TAP 990453N
RTA-TAP 990455N
RTA-TAPW 990653N
RT-CCP 990456
RTM7
RTM7
RTM7
RTM7
RTM9
RTR-TAP 990452
RTR-TAP 990454
SERVICE KIT FOR AMS 500
SNAP1510
SNAP152
SNAP154
SNAP157
SNAP2310
SNAP232
SNAP234
SNAP237
SPDST1SPRC 1SPRC 10SPRC 11SPRC 13SPRC 14SPRC 15SPRC 16SPRC 2SPRC 21SPRC 26
SPRC 27
SPRC 28
SPRC 29
SPRC 30-3
SPRC 4SPRC 5SPRC 6SPRC 7SPRC 8SPRC 9SPRCC 2
UMH
VSP12
VSP16
VSP22
VSP6
VSP68
WM12
WM18
WMTT12
WMTT18

1SNA237086R1700
1SNA237087R1000
1SNA237088R2100
1SNA237131R1000
1SNA237132R1100
1SNA235460R0400
1SNA235097R1000
1SNA235095R1600
1SNA399725R0600
1SNA235158R0100
1SNA235159R0200
1SNA178430R0500
1SNA236000R0400
1SNA236001R2100
1SNA236500R0600
1SNA236501R2300
1SNA235096R1700
1SNA163155R2600
1SNA163167R2200
1SNA164695R2500
1SNA235710R0600
1SNA235711R2300
1SNA235718R0200
1SNA235120R2700
1SNA235117R1000
1SNA235118R2100
1SNA235119R2200
1SNA235126R1100
1SNA235123R1600
1SNA235124R1700
1SNA235125R1000
1SNA235142R2100
1SNA235137R1400
1SNA235463R2300
1SNA235151R2200
1SNA235152R2300
1SNA163007R2600
1SNA173178R0700
1SNB990453R0000
1SNB990455R0000
1SNB990653R0000
1SNB990456R0000
1SNA103115R1300
1SNA103116R1400
1SNA103922R1400
1SNA168410R0700
1SNA164602R0000
1SNB990452R0000
1SNB990454R0000
1SNA360162R1600
1SNA235132R1700
1SNA235129R2400
1SNA235130R2100
1SNA235131R1600
1SNA235136R1300
1SNA235133R1000
1SNA235134R1100
1SNA235135R1200
1SNA360163R1700
1SNA360010R1500
1SNA360020R1700
1SNA360021R0400
1SNA360023R0600
1SNA360024R0700
1SNA360025R0000
1SNA360026R0100
1SNA360011R1500
1SNA360031R0600
1SNA360036R0300
1SNA360037R0400
1SNA360040R2300
1SNA360038R1500
1SNA360039R1700
1SNA360014R0500
1SNA360015R0600
1SNA360016R0700
1SNA360017R0000
1SNA360018R1100
1SNA360019R1200
1SNA360011R0200
1SNK900611R0000
1SNA163432R1400
1SNA173147R2000
1SNA400252R1200
1SNA163433R1500
1SNA206103R0700
1SNA235148R0700
1SNA235149R0000
1SNA235093R1400
1SNA235094R1500

152
152
152
151
151
103
18
18
94
22
22
96
87
153
87
153
18
91
155
155
12
12
12
27
27
27
27
27
27
27
27
28
27
104
30
30
95
89
69
69
70
69
154
154
154
90
90
69
69
81
27
27
27
27
27
27
27
27
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
81
103
58
157
157
157
157
157
100
100
26
26

PAGE 1837

1SNC160023C0201_Index

Type

EASY RAIL DESIGNER 3DTERMINAL BLOCKASSEMBLY SOFTWAREENTRELEC Terminal Blocks

INDUSTRIAL /// ENTRELEC - EASY RAIL DESIGNER 3D

EASY RAIL DESIGNER 3D
From engineering to assembling

ENGINEERING,
DO IT YOURSELF EASILY

Speed up your projects
Simplify the design process

Advanced 3D drawing
and data export

Customized project
management• Built-in 3D viewer• Integration to CAD/CAE softwares• Compatibility with TE printers• Detailed drawings of therail, assembly and markers.

• Management ofmultiple projects• Indication on the drawingof the supplier's, integrator'sand end user's data
• Drawing update indexing
with PDF report.

User-friendly configurator• Intuitive Windows® (1)user interface• Autocorrecting system• Powerful search engine• Insertion of products
external to the database.

(1) Windows® is a registered trademark of Microsoft.

PAGE 2
INDUSTRIAL /// ENTRELEC - EASY RAIL DESIGNER 3D

ASSEMBLING,
RELY ON TE EXPERTISE

Cost effective solution
Up to 20% of material cost reduction

TE technical expertise

Flexible production

Optimized inventory• Drawing technicalverification done by TE
experts• 3 types of assembly:- rail mounted- pre-assembled- packed in kit.

• Products and markers stockedby TE• 100% reliable data import toTE production system.

• Possibility to add some other
TE Din rail products.

• Marking managed by TE• One single product partnumber corresponds to one
complete assembly.

PAGE 3

EASY RAIL DESIGNER 3D

onoff

User-oriented features

3D drawing

CAD/CAE integration• Built-in 3D viewer• 3D drawing export.

• Export to the main CAD/CAE softwares.

Complementary products

Customization• Insertion of products and components(diode, resistor) external to the database.

• Indication on the drawing of the supplier's,
integrator's and end user's name, logotype andpart number.

PAGE 4
INDUSTRIAL /// ENTRELEC - EASY RAIL DESIGNER 3D

Marking

Technical file• Compatibility with TE printers.

• Exportation of the technical file with thedrawings of the rail, assembly and markers
and their bills of material.

SearchAutocorrection• Powerful search engine allowing tofilter per range, function, standard
and technical attributes.

• Intuitive Windows® (1) user interface andautocorrecting system.

(1) Windows® is a registered trademark of Microsoft.

PAGE 5

LET’S CONNECT
We make it easy to connect with our experts and are ready toprovide all the support you need. For additional information or
product assistance, please contact your field representative or
our customer service department. Additional information is alsoavailable on the website http://www.te.com/entrelec.

TECHNICAL SUPPORT
te.com/support-centerAsia:+86 400-820-6015
Europe, Middle East, & Africa:+49 6251-133-0
North America:+1-888-441-9982

te.com
ENTRELEC, TE Connectivity, TE Connectivity (logo) and Every Connection Counts are trademarks. All other logos,
products and/or company names referred to herein might be trademarks of their respective owners.
All other logos, products and/or company names referred to herein might be trademarks of their respective owners.
The information given herein, including drawings, illustrations and schematics which are intended for illustration
purposes only, is believed to be reliable. However, TE Connectivity makes no warranties as to its accuracy orcompleteness and disclaims any liability in connection with its use. TE Connectivity's obligations shall only be as set
forth in TE Connectivity's Standard Terms and Conditions of Sale for this product and in no case will TE Connectivity
be liable for any incidental, indirect or consequential damages arising out of the sale, resale, use or misuse of the
product. Users of TE Connectivity products should make their own evaluation to determine the suitability of eachsuch product for the specific application.
© 2020 TE Connectivity Ltd. family of companies All Rights Reserved.
1-1773980-7

02/20 - Printed in France (PDF)

INDUSTRIAL /// TERMINAL BLOCKS ENTRELEC - MASTER CATALOGTE Connectivity
3, rue Jean Perrin
69687 Chassieu cedex
FranceTel: +33 481923100
www.te.com/