NMR5000
Tank Gauge Receiver
OUTLINE
The NMR5000 is a tank gauge receiver that can accept up to256 transmitters.
Users can access the inside from the front panel side, making
maintenance much easier than with conventional models. The
inner board uses the slot system and supports hot swapping,enabling users to replace the board and other parts during
operation. Although the NMR5000 has no exhaust fan, it
can withstand an ambient temperature of up to 50°C. It isalso lightweight and power-saving. The operating system is
Windows 10 IoT. Simple replacement makes it easy to upgradefrom the existing NMR series and gauge receiver of othercompanies.

STANDARD SPECIFICATIONSFUNCTIONS

Connection❏ Self-diagnosis
Judges whether automatically sampled data are correct
or incorrect. The status of transmitters and interfaces isalso diagnosed.

: Max. 256 transmitters (two-way)External communication : LAN, RS-232C, parallel communication, etc.
Power supply: 100 to 240 V AC ±10% 50/60 Hz

Power consumption: 100 VA (max.)

Cooling fan: N/AAmbient temperature: 0 to 50°C

Ambient humidity: 20 to 80% (No condensation)

Installation: Panel mount, desktop, 19-inch rack

Storage: Solid state drive (SSD)

Panel cutout: 392 (W) × 177 (H) (mm)External dimensions: 388 (W) × 200 (H) × 302 (D) (mm)Mass

: Approx. 10 kg

Maintenance: Front access, hot swapping

Replacement parts: Power supply unit (5 years)*

mountFuse (5 years)
Other parts (7 years)* Figures in parentheses are the recommended replacement
period.

❏ Alarm monitoring
Data are continuously monitored, and when they reach alarm
points, users are immediately notified by lamp and buzzer(contact output is also available). Level alarms can be set
at up to four points, and temperature alarms at up to twopoints for each transmitter.
❏ Level gauge control
Through operations on the display, operators can remotely
perform hoisting up and other operations on level meters.
Operations differ depending on the connected transmitter.
❏ Host computer interface
D a t a o n l e v e l a n d t e m p e r a t u re a re s e n t t o a h o s tcomputer. One port for LAN and two ports for RS-232C serial
communication are provided as standard. Parallel
communication is also available as an option.
❏ Capacity display (optional)
By registering a tank table, the apparent capacity can bedisplayed. The capacity calculated from JIS K-2249 andASTM D-1250 Tables 54A and 54B can also be displayed.

TG-L1034-E01
2nd edition Dec 2019 K
1st edition Dec 2018 K

NMR5000 Tank Gauge ReceiverBASIC MODEL CODE
Basic model code
NMR5000‑‑Description‑IF1 ‑ ✽ ✽✽ ✽IF2
✽ ✽IF3✽ ✽Communication IF4board✽ ✽IF5✽ ✽IF6✽ ✽IF7✽ ✽IF8‑ ✽CN1
✽
CN2
✽
CN3✽
CN4Connectorboard✽
CN5✽
CN6✽CN7✽CN8Internal board specifications* Select one by referring toTable1 "Internal board specification code".

Rear face connector board specifications* Select one by referring toTable2 "Rear face connector board specification code".

N/A
M4 screw terminal 3P‑ 2Amphenol 14P0
1 port for LAN and 2 ports for RS-232C
12 ports for LAN and 1 port for RS-232C
2
1 port for LAN and 3 to 6 ports for RS-232C
32 ports for LAN and 2 to 5 ports for RS-232C
0N/A
1
8.4 inch212.1 inch
0Panel mount
1Desktop
219-inch rack mount319-inch rack mount (front surface alignment)
0 Level and temperature monitoring
1 Custom speciﬁcation‑ 0

Watch dog timer CN9‑ 1

Number of ports for external communication

Display

Installation

Software basic specifications

Table1: Internal board specification codeSpecifications
No boards
Two-way communication board

One-way communication board

Two-way communication board
other company (MDP/V1 format)
Digital input board(input: 32 points)

Digital input/output board(input: 16 points, output: 16 points)

Digital output board(output: 32 points)
Analog input board(input: 4 points)
Analog output board(output: 4 points)

FW/DM-II format
DM format
DB-M format (36V)
DB-ML format
DB-M format (24V)
Ch1: Other company format
Ch2: Other company format
Ch1: Other company format
Ch2: TIC format
Photocoupler input (internal power supply)
Photocoupler input (external power supply)
Photocoupler input (internal power supply)
Photocoupler output (internal power supply)
Photocoupler input (external power supply)
Photocoupler output (external power supply)
Photocoupler input (internal power supply)
Photo relay outputPhotocoupler input (external power supply)
Photo relay output
Photocoupler input (internal power supply)
Photo relay output (output: 8 points) ✽1
Photocoupler input (external power supply)
Photo relay output (output: 8 points) ✽1
Photocoupler output (internal power supply)
Photocoupler output (external power supply)
Photo relay output
Photo relay output (output: 16 points) ✽1
Current input
Voltage input
Current input
Voltage input

Table 2: Rear face connector board specification code
Code0 0W 0S 0
S 1
S 2
S 3E0E111012021222324253333445501230
10
1Specifications
No connectors
M4 screw terminal 6P
Plug type terminal
Amphenol 36PAmphenol 50P
D-sub 9P (male) inch screw

Code012345✽1: Specification when using 2-line communication for a single output signal, in which eachoutput is isolated and the number of output points is halved.

2TOKYO KEISO CO., LTD.

TG-L1034-E01

NMR5000 Tank Gauge Receiver

INDICATION
The touch panel LCD can display the following:● Main menu
● One tank
● Tank list (8 tanks and 16 tanks)● Tank graph (2 tanks and 4 tanks)● Tank status (error, level alarm, temp. alarm)● Slot status● Status summary (error summary and alarm summary)

EXAMPLE OF DISPLAY

TG-L1034-E01

Main menu

One tank

List (8 tanks)

List (16 tanks)

Graph (2 tanks)

Graph (4 tanks)
TOKYO KEISO CO., LTD.

3

NMR5000 Tank Gauge Receiver

4Tank status (error)

Tank status (level alarm)

Tank status (temp. alarm)

Slot status

Status summary (error summary)Status summary (alarm summary)TOKYO KEISO CO., LTD.

TG-L1034-E01

NMR5000 Tank Gauge Receiver

EXTERNAL DIMENSIONS

Unit: mm

〔Display size: 8.4 inch〕
302
6388

22230

44

Front View

172

132.5

200

200

NMR5000

Side View〔Display size: 12.1 inch〕

302

6388

2244230

236
132.5

264

264

NMR5000

Front View

Side View〔No display size〕
370

13230

24.5

132.5

132.5

NMR5000

Front View

TG-L1034-E01

Side View

TOKYO KEISO CO., LTD.

5

NMR5000 Tank Gauge Receiver〔Display size: 8.4 inch〕〔Common〕
414392
370

4-6φ

132.5

177140CN1CN2CN3CN4CN5CN6CN7CN8CN9LAN1LAN2COM1 COM2 COM3 COM418.5

AC-IN

Rear View

Panel Cut Dimension〔Display size: 12.1 inch〕
4144-6φ

18.5140241392

Panel Cut Dimension* Specification is subject to change without notice.

Head Office : Shiba Toho Building, 1 – 7 – 24 Shibakoen, Minato-ku, Tokyo 105 – 8558
Tel : +81-3 – 3431 – 1625 (KEY) ; Fax : +81-3 – 3433 – 4922
e-mail : overseas.sales@tokyokeiso.co.jp ; URL : https://www.tokyokeiso.co.jp
6TG-L1034-E01