SNACOMPACTTERMINAL BLOCKS – SCREW CLAMP TECHNOLOGYSNACompact Terminal blocks

General contents
SNACompact terminal blocks
Screw clamp technology

Features & Benefits..............................................................................p. 3
Selection guide......................................................................................p. 6
SNACompact Terminal blocks offering........................................p. 8
Accessories........................................................................................... p. 68
Marking system & accessories...................................................... p. 79
CrossReference table....................................................................... p. 86

Summary_1

Index....................................................................................................... p. 87

3-1773983-5_EN - Edition February 2021

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 1INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 2

SNACompact Terminal blocks
Features & Benefits

SNACOMPACT
SMALL IS BIG!
SMALL IS BIG WITH SNACOMPACT TERMINALBLOCKS THAT HELP TO IMPROVE PANELBUILDING PROCESS PROVIDING COMPACT
AND PERFORMANT PRODUCTS RELYING ON
MORE THAN 60 YEARS OF TRACK-RECORD

Benefit from high performancesin smaller space

Improve your panelbuilding process• Secure your wiring with ENTRELEC screw clamp featuring• Optimize the installation, wiring and connection, by taking
benefit from ENTRELEC design, screwless groundconnection, well aligned fuse and disconnect version• Save up to 14% in height for 2.5 and 4 mm² versus SNA-type
terminal blocks, which allows to fit in smaller junction boxes• Provide for a long lifetime on site time-tested by 60 years
track record on screw technology, fire resistant V0 plastic
grade and installation in harsh environments.

• Reduces mounting errors thanks to asymmetrical design
and by using compatible TE Connectivity’s end ferrules andcrimping tools• Improve the layout & identification of the panel by using
TE Connectivity’s large cable management portfolio,
including identification labels, card and roll printing systems,
cable ties and cable wrapping accessories• Save time when designing your panel thanks to
TE Connectivity’s digital tools, such as TE.COM and Easy
Rail Designer 3D CAD software allowing complete rail
assembly design and 3D viewing functionality.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 3

1SNC160267S0201

hardened steel, anti-release system, funnel entry for
conductor, tab under clamp

SNACompact Terminal blocks
Features & Benefits

IMPROVE YOURPANEL BUILDING PROCESSWITH SNACOMPACT

BENEFIT FROM HIGH PERFORMANCES IN SMALLER SPACE

Secure your wiring with ENTRELEC
screw clamp featuring hardened steel,anti-release system, funnel entry for
conductor, tab under clamp.
The SNACompact screw clamp is
designed to reduce accidental releases
due to vibrations, shocks or evenabusive cable draw and can
fit up to two conductors per clamp
which offers extended possibilities inelectrical cabinets.

Screw

The TE Connectivity anti-releasesystem creates a controlledlocking-screw effect thanks to the2 overlapping tabs that maintainthe clamp parts.
The screw is locked with safety.
The retightening campaigns are
not needed anymore!

The clamp is punched,which increases thenumber of screw threads
by 30 % meaning a hightorque resistanceScrew clamp
Conductive
linking bar
Stripped wire

The screw tightens
the conductive bar tothe cable. There is no
torsion effect applied
to the cable

Hardened steel makes theconnection very reliable
Flap avoiding the insertion ofcable underneath the clamp

Save up to 14% in height for 2.5 and
4 mm² versus legacy terminal blocks,
which allows to fit in smaller junction
boxes.

-14%

Reduced size junction box with SNACompact

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

1SNC160227S0201 - Rev. A

Provide for a long lifetime on site proven by 60 years
track record on screw technology, fire resistant V0
plastic grade and installation in harsh environments.
SNACompact terminal blocks have been tested upon
many environmental tests:• Vibrations: IEC 60068-2-6 standard• Corrosion: salt mist as per IEC 60068-2 §11• Flammability: UL94V0 & needle burning test
(IEC 60947-7-1 §8.4.6)• Short-circuit: IEC 60947-7-1 §8.4.6.

PAGE 4

SNACompact Terminal blocks
Features & Benefits

IMPROVE YOUR PANEL BUILDING PROCESSReduces mounting errors thanks to asymmetrical design andby using compatible TE Connectivity’s end ferrules andcrimping tools.

Improve the layout & identification of the panel by using
TE Connectivity’s large cable management portfolio, including
identification labels, card and roll printing systems, cable ties
and cable wrapping accessories.

Save time when designing your panel thanks to
TE Connectivity’s digital tools, such as TE.COM providing in
few clicks the technical datasheets, cross-references,
accessory compatibility, 2D/3D models and fast sample
ordering possibility, and Easy Rail Designer 3D CAD software
allowing rail assembly design and 3D viewing functionality.

1SNC160227S0201 - Rev. A

Optimize the installation, wiring and connection, by taking
benefit from Entrelec design, screwless ground connection,aligned fuse and disconnect version.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 5

SNACompact Terminal blocks
Selection guideFeed-throughGroundSectionIEC

UL/CSA

2.5 mm²

12 AWG

C2.5/5C2.5/5.P

10 AWG

C2.5/6

C2.5/6.P

4 mm²

10 AWG

C2.5/6* ; C4/6

6 mm²

8 AWG

C6/8

10 mm²

6 AWG

C10/10C10/10.P

16 mm²

4 AWG

C16/12

M16/12.P

35 mm²

0 AWG

M35/16

M35/16.P

70 mm²00 AWG

D70/22

D70/22.P

95 mm²0000 AWG

D95/26

D95/26.P

M4/6.3A

M4/6.4A

C4/6.P

M4/6.3A.P

M4/6.4A.P

C6/8.P*: manufacturer wiring data

Double deck

Triple deck

SectionIEC

2.5 mm²

UL/CSA

12 AWG

MA2.5/5.D2

MA2.5/5.D1

10 AWG
12 AWG

M4/6.D2

M4/6.D1

8 AWG

M6/8.D2

M6/8.D1

M4/6.DD

M4/6.DD1

D4/6.T3

D4/6.T1

D4/6.T3.P

1SNC160229S0201 - Rev. A

4 mm²
6 mm²

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 6

SNACompact Terminal blocks
Selection guide

Test and Measurement
Disconnect with blade

For 5 x 20 mm fuses

Disconnect with sliding link

SectionIEC

UL/CSA

2.5 mm²

12 AWG

MA2.5/5.SNB

4 mm²

12 AWG

C4/6.S

M4/6.D2.SNBT

C4/8.SF

M4/8.SFD

M4/8.D2.SF M4/8.D2.SFD3

M4/8.SFD3

M4/8.D2.SFL

M4/8.SFL
10 AWG

M4/6.SNB

8 AWG

M6/8.SNB

C4/6.SF

C4/6.SFD24
C4/6.SFD250

6 mm²

M6/8.ST1

C6/8.ST1.IP20

C6/8.ST1

Sensor/actuator

Thermocouple Miniblocks

SectionIEC

UL/CSA

MTC6

0.9 to 1.5mm Dia.
1.5 mm²

DR1.5/4

2.5 mm²
4 mm²

D2.5/6.D

DR1.5/5

D2.5/6.DL

12 AWG

DR4/6

DR4/6.P

1SNC160229S0201 - Rev. A

10 AWG

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 7

SNACompact range

Terminal blocks Screw clamp technology

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 8

SNACompact range

Terminal blocks Screw clamp technology

Offer Contents
Feed-through
2,5 mm²/12 AWG
2,5 mm²/10 AWG
4 mm²/10 AWG

6 mm²/8 AWG
10 mm²/6 AWG
16 mm²/4 AWG
35 mm²/0 AWG
70 mm²/00 AWG
95 mm²/0000 AWG

Ground2,5 mm²/12 AWG
2,5 mm²/10 AWG
4 mm²/10 AWG

6 mm²/8 AWG
10 mm²/6 AWG
16 mm²/4 AWG
35 mm²/0 AWG
70 mm²/00 AWG
95 mm²/0000 AWG

Double deck

2,5 mm²/12 AWG
4 mm²/12 AWG
4 mm²/10 AWG
4 mm²/12 AWG
6 mm²/8 AWG

Triple deck

4 mm²/12 AWG

C2.5/5......................................................................................p. 10
C2.5/6......................................................................................p. 11
C4/6 ........................................................................................p. 12
M4/6.3A..................................................................................p. 13
M4/6.4A..................................................................................p. 14
C6/8.........................................................................................p. 15
C10/10 ...................................................................................p. 16
C16/12 ...................................................................................p. 17
M35/16....................................................................................p. 18
D70/22....................................................................................p. 19
D95/26....................................................................................p. 20
C2.5/5.P .................................................................................p. 21
C2.5/6.P..................................................................................p. 22
C4/6.P.....................................................................................p. 23
M4/6.3A.P..............................................................................p. 24
M4/6.4A.P..............................................................................p. 25
C6/8.P.....................................................................................p. 26
C10/10.P.................................................................................p. 27
M16/12.P................................................................................p. 28
M35/16.P................................................................................p. 29
D70/22....................................................................................p. 30
D95/26.P................................................................................p. 31
MA2.5/5.D2 ..........................................................................p. 32
MA2.5/5.D1.1 ......................................................................p. 33
M4/6.D2..................................................................................p. 34
M4/6.D1..................................................................................p. 35
M4/6.DD.................................................................................p. 36
M4/6.DD1...............................................................................p. 37
M6/8.D2..................................................................................p. 38
M6/8.D1 .................................................................................p. 39
D4/6.T3...................................................................................p. 40
D4/6.T1...................................................................................p. 41

Disconnect with blade
2,5 mm²/12 AWG
4 mm²/10 AWG
6 mm²/8 AWG
4 mm²/12 AWG

MA2.5/5.SNB........................................................................p. 42
C4/6.S......................................................................................p. 43
M4/6.SNB...............................................................................p. 44
M6/8.SNB...............................................................................p. 45
M4/6.D2.SNBT.....................................................................p. 46

Test and Measurement

Typical schematics for measuring devices..................................................................p. 48
6 mm²/8 AWG
C6/8.ST1.................................................................................p. 49
C6/8.ST1.IP20 .....................................................................p. 50
M6/8.ST1 ...............................................................................p. 51

For 5 x 20 mm fuses
4 mm²/10 AWG
4 mm²/12 AWG

C4/6.SF ..................................................................................p. 53
C4/6.SFD ..............................................................................p. 54
C4/8.SF...................................................................................p. 55
M4/8.SFD3 ............................................................................p. 56
M4/8.SF..................................................................................p. 57
M4/8.D2.SF............................................................................p. 58

Thermocouple

MTC6...........................................................................p. 60

Sensor/Actuator

D2.5/6.D...................................................................p. 61
D2.5/6.DL.................................................................p. 62

Miniblocks

1.5 mm²
1.5 mm² /12 AWG
4 mm²/12 AWG

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

DR1.5/4...................................................................................p. 64
DR1.5/5...................................................................................p. 65
DR4/6......................................................................................p. 66
DR4/6.P..................................................................................p. 67

PAGE 9

Summary_1_intermedaire

Marshalling cabinets application.......................................................p. 63

C2.5/5 screw clamp terminal blocks
Feed-through - 5 mm 0.2 in spacing

COMPACT

2.5 mm²
12 AWG

Description–– 2.5 mm² feed-through terminal with TE screw clamp connection,–– Save space by connecting conductors up to 4 mm² in just 5 mm 0.197 in spacing.

Ordering details
Description

1SNC161327V0014

Feed-throughColor
2 connections

Grey
Blue

49 1.93"41.5 1.63"

43.6 1.72"

C2.5/5C2.5/5.N

Main technical data

Part Numbers
1SNL605010R0000
1SNL605020R0000

Pkg

Weightqty(1 pce) g

100
100

5.5
5.5

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²
0.2 ... 2.5 mm²
0.2 ... 4 mm²
0.2 ... 2.5 mm²A3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²
24 A / 2.5 mm²
300 A

24 ... 12 AWG

Wire stripping
length1000 V
8000 VIP20

600 V

1 conductor
per clamp

C2.5/5Type

24 ... 12 AWG
24 ... 14 AWG
24 ... 16 AWG

Tool

24 ... 18 AWG
20 A / 12 AWG
TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 3.5 mm
Ø 0.14 in

0.5 N.m ± 0.1
4.4 lb.in ± 0.9

NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

22 0.87"

5 mm 0.2 in spacing

Accessories
Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
9 mm
End sections
1
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
10 polesCircuit separators
Terminal block
Blank card
markers

End stops

Color
0.394 in
0.354 in
0.039
24 (IEC)
24 (IEC)
24 (IEC)
24 (IEC)
24 (IEC)
30 (IEC)
30 (IEC)

Grey
Grey
Grey

Grey
Grey
White

Type
BAM4
BAZ1
EP5-6
BJCI5-2
BJCI5-3
BJCI5-4
BJCI5-5
BJCI5-10
PC5-2
PC5-10CS5-6
RC510TT
RC510

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNL905602R0000
1SNL905603R0000
1SNL905604R0000
1SNL905605R0000
1SNL905610R0000
1SNA113542R1000
1SNA113544R1200
1SNL900101R0000
1SNA231600R1500
1SNA231000R0700

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
22
10

12,00
4.70
1.6
3.95
5.9
7.9
9.87
19.7
1.80
6.00
1.16
12.00
5.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Green-yellow

TypeC2.5/5.PPart Numbers
1SNL605150R0000

Pkg

Weightqty(1 pce) g

100

8.5

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 10

1SNC161174S0201 - Rev. A

1

C2.5/6 screw clamp terminal blocks
Feed-through - 6 mm 0.24 in spacing

COMPACT

2.5 mm²
10 AWG

Description–– 2.5 mm² feed-through terminal with TE screw clamp connection

Ordering details
Description

1SNC161312F0014

Feed-throughC2.5/649 1.93"41.5 1.63"

43.6 1.72"

Color
2 connections

Type
Grey
Blue

C2.5/6
C2.5/6.N

Main technical data

Part Numbers
1SNL606011R0000
1SNL606021R0000

Pkg

Weightqty(1 pce) g

100
100

6.4
6.4

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 2.5 mm²A3
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²
0.2 ... 1.5 mm²
24 A / 2.5 mm²
300 A

24 ... 10 AWG

Wire stripping
length1000 V
8000 VIP20

600 V

1 conductor
per clamp

24 ... 10 AWG
24 … 12 AWG
24 ... 14 AWG

Tool

24 ... 16 AWG
25 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 in

0.5 N.m ± 0.1
4.4 lb.in ± 0.9

NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

17.5 0.69"

6 mm 0.24 in spacing

Accessories
1

Description

2
1

3

5

4

2
3

4

5
6

10 mm
9 mm
End sections
1
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
3 poles
4 poles
10 poles25 poles
50 polesCircuit separators
Terminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.039
32 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
24 (IEC)
24 (IEC)

Grey
Grey
Grey

Grey

Black
Grey
White

Type
BAM4
BAZ1
EP5-6
BJCI6-2
BJCI6-3
BJCI6-4
BJCI6-5
BJCI6-10
PC6-2
PC6-3
PC6-4
PC6-10LJB6-25E
LJB6-50
CS5-6
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNL906602R0000
1SNL906603R0000
1SNL906604R0000
1SNL906605R0000
1SNL906610R0000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNL906751R0000
1SNL906750R0000
1SNL900101R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
10
10
22
10

12,00
4.70
1.6
3.95
5.9
7.9
9.87
19.7
2.00
2.00
3.00
8.00
17.5
25.5
1.16
12
7.50

Ground screw clamp terminal blocks
Description
GroundColor
Green-yellow

TypeC2.5/6.PPart Numbers
1SNL606151R0000

Pkg

Weightqty(1 pce) g

100

10.2

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT - TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 111SNC161175S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

C4/6 screw clamp terminal blocks
Feed-through - 6 mm 0.24 in spacing

COMPACT

Description

4 mm²–– 4 mm² feed-through terminal with TE screw clamp connection

10 AWG

Ordering details
Description

1SNC161312F0014

Feed-throughC4/6

49 1.93"41.5 1.63"

43.6 1.72"

Color
2 connections

Type
Grey
Blue

C4/6
C4/6.N

Main technical data

Part Numbers
1SNL606010R0000
1SNL606020R0000

Pkg

Weightqty(1 pce) g

100
100

6.4
6.4

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.2 ... 6 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²A4
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
32 A / 4 mm²
480 A

24 ... 10 AWG

Wire stripping
length1000 V
8000 VIP20

600 V

1 conductor
per clamp

24 ... 10 AWG
24 … 12 AWG
24 ... 14 AWG

Tool

24 ... 16 AWG
30 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 in

0.65 N.m ± 0.15
5.75 lb.in ± 1.35

NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

17.5 0.69"

6 mm 0.24 in spacing

Accessories
Description

2
1

3

4

5

6

2
3

4

5
6

10 mm
9 mm
End sections
1
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
3 poles
4 poles
10 poles25 poles
50 polesCircuit separators
Terminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.039
32 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
24 (IEC)
24 (IEC)

Grey
Grey
Grey

Grey

Black
Grey
White

Type
BAM4
BAZ1
EP5-6
BJCI6-2
BJCI6-3
BJCI6-4
BJCI6-5
BJCI6-10
PC6-2
PC6-3
PC6-4
PC6-10LJB6-25E
LJB6-50
CS5-6
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNL906602R0000
1SNL906603R0000
1SNL906604R0000
1SNL906605R0000
1SNL906610R0000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNL906751R0000
1SNL906750R0000
1SNL900101R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
10
10
22
10

12,00
4.70
1.6
3.95
5.9
7.9
9.87
19.7
2.00
2.00
3.00
8.00
17.5
25.5
1.16
12
7.50

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Green-yellow

TypeC4/6.PPart Numbers
1SNL606150R0000

Pkg

Weightqty(1 pce) g

100

10.2

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 121SNC161176S0201 - Rev. A1

M4/6.3A screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing

4 mm²
10 AWG

Description–– Ease one potential distribution on 3 independent screw clamps,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161115F0014

Feed-throughM4/6.3A
M4/6.3A.N

Grey
Blue

1SNA115468R2000
1SNA125468R2200

Main technical data

Mounting instructions

Connecting capacity
1 conductor
per clamp

IEC

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-10 AWG

12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

M4/6.3A

55.5 2.18"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

32 A / 4 mm²
480 A
800 V
8000 VIP20

20 A / 10 AWG 25 A / 12 AWG
600 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.TE.com

48 1.89"

53 2.09"51.5 2.03"5050Weight(1 pce) g
11.00
11.00

CE

RoHS

USR

CSA

Gost R

25 0.98"
30 1.18"

6 mm 0.236 in spacing

Accessories
Description
1

2

1
2
3

3

4

5

6

4
5

7

9

8

6
7
8
9

Color

10 mm
0.394 in
9 mm
0.354 inEnd sections
3 mm
0.118 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
35 A
10 polesCross spacing
5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 injumpers
Universal screw jumper bar kit N°I
Universal screw jumper bar kit N°III
Insulating tips
For lateral jumper bars type PC...
Circuit separators
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 inTerminal block
Blank card
markers
End stops

Grey
Grey

Grey

Grey

White

Type
BAM4
BAZ1
FEM3A
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
PC6-2
PC6-10
EL6
BJDP1
BJDP3
EIP
SCM6
AL2
AL3
RC610TT
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116576R1500
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA113546R1400
1SNA113548R2600
1SNA173627R2100
1SNA179623R0300
1SNA179625R0500
1SNA113550R2400
1SNA113003R1000
1SNA163043R2100
1SNA163261R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
10
10
50
50
22
1

12.00
4.70
3.30
4.40
6.70
8.90
11.20
22.40
2.00
8.00
0.10
7.00
5.00
0.30
0.90
1.20
12
7.50

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with M4/6.3A.P...

Green-yellow

TypeM4/6.3A.P

Part Number
1SNA195637R1200

Pkg

Weightqty(1 pce) g

50

22.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 13

1SNC161118S0201 - Rev. C

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

M4/6.4A screw clamp terminal blocks
Feed-through - 6 mm 0.236 in spacing

Description

4 mm²–– Ease one potential distribution on 4 independent screw clamps,–– Flexibility: snap onto symmetrical and asymmetrical rails.

10 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

Weight(1 pce) g
20.00
20.00

qty

1SNC161012F0014

Feed-throughM4/6.4A
M4/6.4A.N

Grey
Blue

1SNA115479R2300
1SNA125479R2500

Main technical data

Mounting instructions

Connecting capacity
1 conductor
per clamp

IEC

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-10 AWG

12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

M4/6.4A

55.5 2.18"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

32 A / 4 mm²
480 A
800 V
8000 VIP20

20 A / 10 AWG 25 A / 12 AWG
600 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

48 1.89"

53 2.09"63.5 2.50"

50
50

CE

RoHS

USR

CSA

Gost R

25 0.98"
30 1.18"

6 mm 0.236 in spacing

Accessories
Description
2

1
2
3

3

4

5

6

4
5

7

9

8

6
7
8
9

10 mm
0.394 in
9 mm
0.354 inEnd sections
3 mm
0.118 inJumper bars
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
35 A
10 polesCross spacing
5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 injumpers
Universal screw jumper bar kit N°I
Universal screw jumper bar kit N°III
Insulating tips
For lateral jumper bars type PC...
Circuit separators
Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 inTerminal block
Blank card
markers
End stops

Grey
Grey

Grey

Grey

White

Type
BAM4
BAZ1
FEM4A
BJMI6-2
BJMI6-3
BJMI6-4
BJMI6-5
BJMI6-10
PC6-2
PC6-10
EL6
BJDP1
BJDP3
EIP
SCM6
AL2
AL3
RC610TT
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116629R2200
1SNA176663R0000
1SNA176664R0100
1SNA176665R0200
1SNA176666R0300
1SNA176667R0400
1SNA113546R1400
1SNA113548R2600
1SNA173627R2100
1SNA179623R0300
1SNA179625R0500
1SNA113550R2400
1SNA113003R1000
1SNA163043R2100
1SNA163261R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
10
10
10
10
50
50
22
1

12.00
4.70
3.80
4.40
6.70
8.90
11.20
22.40
2.00
8.00
0.10
7.00
5.00
0.30
0.90
1.20
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with M4/6.4A.P...

Green-yellow

TypeM4/6.4A.P

Part Number
1SNA195638R2300

Pkg

Weightqty(1 pce) g

50

22.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 141SNC161119S0201 - Rev. C

1

Color

C6/8 screw clamp terminal blocks
Feed-through - 8 mm 0.31 in spacing

COMPACT

Description

6 mm²–– 6 mm² feed-through terminal with TE screw clamp connection

8 AWG

Ordering details
Description

1SNC161315F0014

Feed-throughC6/8

48 1.89"

55.5 2.19"

45.5 1.79"

Color
2 connections

Type
Grey
Blue

C6/8
C6/8.N

Main technical data

Part Numbers
1SNL608010R0000
1SNL608020R0000

Pkg

Weightqty(1 pce) g

50
50

12.8
12.8

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²A5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
41 A / 6 mm²
720 A

20 ... 8 AWG

Wire stripping
length1000 V
8000 VIP20

600 V

1 conductor
per clamp

20 ... 8 AWG
20 ... 10 AWG
20 ... 12 AWG

Tool

20 ... 14 AWG
45 A / 8 AWG
TorqueTH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 4-5 mm
Ø 0.16-0.2 in

0.9 N.m ± 0.1
8 lb.in ± 0.9

NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

23.9 0.94"

8 mm 0.31 in spacing

Accessories
1

Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
9 mm
End sections
2.8
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
10 polesCircuit separators
Terminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.110
41 (IEC)
41 (IEC)
41 (IEC)
41 (IEC)
41 (IEC)
50 (IEC)
50 (IEC)

Grey
Grey
Grey

Black
Grey
White

Type
BAM4
BAZ1
FEM6
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
PC8-2
PC8-10SCM6RC810TT
RC810

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA116538R1700
1SNA163313R2400
1SNA113003R1000
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
10
22
10

12,00
4.70
2.40
4.50
6.00
10.00
12.20
20.00
3.00
14.00
0.30
12
8.20

Ground screw clamp terminal blocks
Description

Color

GroundGreen-yellow

TypeC6/8.PPart Numbers
1SNL608150R0000

Pkg

Weightqty(1 pce) g

50

15.2

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 15

1SNC161177S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

C10/10 screw clamp terminal blocks
Feed-through - 10 mm 0.39 in spacing

COMPACT

Description

10 mm²–– 10 mm² feed-through terminal with TE screw clamp connection

6 AWG

Ordering details
Description

1SNC161318F0014

Feed-throughC10/1048 1.89"

55.5 2.19"

42.7 1.68"

Color
2 connections

Type
Grey
Blue

C10/10C10/10.N

Main technical data

Part Numbers
1SNL610010R0000
1SNL610020R0000

Pkg

Weightqty(1 pce) g

50
50

16.1
16.1

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
B6
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
57 A / 10 mm²1200 A

20 ... 6 AWG

Wire stripping
length1000 V
8000 VIP20

600 V

1 conductor
per clamp

20 ... 6 AWG
20 ... 8 AWG
20 ... 10 AWG

Tool

20 ... 12 AWG
59 A / 6 AWG
TorqueTH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 5.5-6 mm
Ø 0.22-0.24 in

1.3 N.m ± 0.1
11.5 lb.in ± 0.9

NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

23.9 0.94"

10 mm 0.39 in spacing

Accessories
Description

2
1

3

4

5

6

2
3

4
5
6

10 mm
9 mm
End sections
2.8
Jumper bars
2 poles
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
Circuit separators
Terminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.110
57 (IEC)
57 (IEC)
57 (IEC)
57 (IEC)
57 (IEC)
70 (IEC)

Grey
Grey

Grey
White

Type
BAM 4
BAZ1
FEM6
BJMI10-2
BJMI10-3
BJMI10-4
BJMI10-5
BJMI10-10
PC10-10SCM6RC810TT
RC1010Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA176675R0400
1SNA176676R0500
1SNA176677R0600
1SNA176678R1700
1SNA176679R1000
1SNA163315R2600
1SNA113003R1000
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
10
22
10

12,00
4.70
2.40
5
8.00
11.00
13.00
27.00
23.00
0.30
12
1.30

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Ground screw clamp terminal blocks
Description
GroundColor
Green-yellow

Type
C10/10.P

Part Numbers
1SNL610150R0000

Pkg

Weightqty(1 pce) g

50

22.5

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 16

1SNC161178S0201 - Rev. A

1

C16/12 screw clamp terminal blocks
Feed-through - 12 mm 0.47 in spacing

COMPACT

Description

16 mm²–– 16 mm² feed-through terminal with TE screw clamp connection

4 AWG

Ordering details
Description

1SNC161330V0014

Feed-throughC16/1248 1.89"

55.5 2.19"

42.7 1.68"

Color
2 connections

Type
Grey
Blue

C16/12
C16/12.N

Main technical data

Part Numbers
1SNL612010R0000
1SNL612020R0000

Pkg

Weightqty(1 pce) g

50
50

18
18

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)
Short Circuit Current Rating (with specific conditions)
Rated voltage
Impulse withstand voltage
Protection

0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²
0.5 ... 16 mm²B60.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
76 A / 16 mm²
1920 A

20 ... 4 AWG

Wire stripping
length1000 V
8000 VIP20

600 V

1 conductor
per clamp

20 ... 4 AWG
20 ... 6 AWG
20 ... 8 AWG

Tool

20 ... 10 AWG
80 A / 4 AWG
TorqueTH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 5.5-6 mm
Ø 0.22-0.24 in

1.3 N.m ± 0.1
11.5 lb.in ± 0.9

NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

23.9 0.94"

12 mm 0.47 in spacing

Accessories
1

3

5

Description

2

4

Color

1

End stops

10 mm
9 mm
2.8
2 poles
3 poles
4 poles
5 poles
10 poles2
3

End sections
Jumper bars

4
5

Circuit separators
Terminal block
Blank card
markers

0.394 in
0.354 in
0.110
76 (IEC)
76 (IEC)
76 (IEC)
76 (IEC)
76 (IEC)

Grey
Grey
Grey

Grey
White

Type
BMA4
BAZ1
FEM6
BJMI12-2
BJMI12-3
BJMI12-4
BJMI12-5
BJMI12-10
SCM6RC810TT
RC1010Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA179626R0600
1SNA179628R1000
1SNA179629R1100
1SNA179630R1600
1SNA179631R0300
1SNA113003R1000
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
22
10

12,00
4.70
2.40
6.00
9.00
13.00
16.00
33.00
0.30
12
1.30

Ground screw clamp terminal blocks
Description

Color

GroundGreen-yellow

Type
M16/12.PPart Numbers
1SNA165130R2300

Pkg

Weightqty(1 pce) g

20

40

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 17

1SNC161179S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

M35/16 screw clamp terminal blocks
Feed-through - 16 mm 0.630 in spacing

35 mm²0 AWG

Description–– Closed terminal block: no end section needed, optimized rigidity,–– Flexibility: snap onto symmetrical and asymmetrical rails,–– Use of jumper bars requires the user to cut out the partition.

Ordering details
Description

Color

Type

Part Number

Pkg

Weight(1 pce) g
50.00
50.00
50.00
50.00
50.00
50.00
50.00

1SNC161110F0014

qty

Feed-throughClosed block withpartition

M35/16
M35/16.N
M35/16
M35/16
M35/16
M35/16
M35/16

Grey
Blue
Yellow
Red
White
Black
Beige

1SNA115124R0700
1SNA125124R0100
1SNA105124R1600
1SNA400195R2200
1SNA400196R2300
1SNA400194R2100
1SNA195124R0000

Main technical data

Mounting instructions

Connecting capacity

M35/16

1 conductor
per clamp

22 0.87"
27 1.06"

IEC

Rigid: Solid/Stranded
6-50 mm²
Flexible without ferrule
6-35 mm²
Flexible with insulated ferrule
Gauge
B9

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

10-0 AWG

10-0 AWG

Wire stripping
length

17 mm
0.669 inTool

Flat screwdriverØ 6.5 - 7 mm
Ø 0.255 - 0.276 in

1.5 0.05"

61.5 2.42"
54 2.12"59 2.32"

49 1.93"

20
20
20
20
20
20
20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

125 A / 35 mm² 150 A / 0 AWG 150 A / 0 AWG
4200 ATorque1000 V
600 V
600 V
8000 VIP10
NEMA

2.8 - 3 N.m
24.9 - 26.7 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

16 mm 0.630 in spacingRoHS

USR CNR

CSA

Gost R

Accessories
Description
2

1
2

3

4
3

5

7

6

8

4
5
6
7
8

Color

10 mm
0.394 in
9 mm
0.354 inJumper bars
2 poles
125 A
3 poles
4 poles
5 poles
10 polesCross spacing
Universal screw jumper bar kit N°I
jumpers
Universal screw jumper bar kit N°II
Circuit separators 3 mm
0.118 in
Test sockets
DIA 4 mm 0.157 in
Test plugs
DIA 4 mm 0.157 inProtecting covers Length 1 m 39 in
Terminal block
Blank card
markers
End stops

Grey
OrangeGrey
WhiteTransparent
White

Type
BAM4
BAZ1
JB16-2
JB16-3
JB16-4
JB16-5
JB16-10BJDP1
BJDP2
SCFCV1-2
AL4-M4FC4
CPV1-2
RC810TT
RC1010Part Number
1SNK900001R0000
1SNK900002R0000
1SNK916302R0000
1SNK916303R0000
1SNK916304R0000
1SNK916305R0000
1SNK916310R0000
1SNA179623R0300
1SNA179624R0400
1SNA116795R1100
1SNA206723R0300
1SNA167860R0100
1SNA176816R1200
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
50
10
10
10
10
10
10
10
10
50
10
1
22
10

12.00
4.70
10.20
16.00
21.80
27.60
56.60
7.00
6.00
8.00
1.30
12
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with M35/16...

Green-yellow

Type
M35/16.PPart Number
1SNA165111R1400

Pkg

Weightqty(1 pce) g

20

50.50

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 18

1SNC161022S0201 - Rev. D

1

D70/22 screw clamp terminal blocks
Feed-through - 22 mm 0.866 in spacing

Description

70 mm²–– Closed terminal block: no end section needed, optimized rigidity,–– Use of jumper bars requires the user to cut out the partition.

00 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161057F0014

Feed-throughClosed blockD70/22
D70/22.N
D70/22.YL

Grey
Blue
Yellow

1SNA400305R1000
1SNA400306R1100
1SNA400789R0000

Main technical data

Mounting instructions

Connecting capacity
1 conductor
per clamp

IEC

Rigid: Solid/Stranded
16-95 mm²
Flexible without ferrule
16-70 mm²
Flexible with insulated ferrule
Gauge
B11

UL

CSA

Rail

TH 35-7.5,
TH 35-15

4-00 AWG

4-00 AWG

Wire stripping
length25 mm
0.98 inTool

Allen keyØ 6 mmØ 0.236 in

D70/22

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
84 3.30"

1.3 .05"

76.5 3.01"

74.5 2.92"

10
10
10

Weight(1 pce) g
158.10158.10158.10192 A / 70 mm² 159 A / 00 AWG 159 A / 00 AWG
8400 ATorque1000 V
600 V
600 V
8000 VIP10
NEMA

6 - 7 N.m
53.4 - 62.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

CB

RoHS

USR CNR

CSA

Gost R

39.5 1.55"

22 mm 0.866 in spacing

Accessories
Description
2

3

4

5

1
2

3
4
5

Color

12 mm
0.472 in
2 poles
192 A
3 poles
5 poles
10 polesCircuit separators 3 mm
0.118 inProtecting covers Transparent, length 1 m 39 in
Terminal block
Blank card
markers
End stops
Jumper bars

Grey

Grey
Transparent
White

Type
BAZH1
JB22-2
JB22-3
JB22-5
JB22-10SCFCV4CPV4-5
RC810TT
RC1010Part Number
1SNK900102R0000
1SNK922302R0000
1SNK922303R0000
1SNK922305R0000
1SNK922310R0000
1SNA116797R1300
1SNA176791R2100
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
5
5
5
5
10
1
22
1

24.00
27.00
43.30
76.10
157.4012
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with D70/22...

Green-yellow

Type
D70/22.PPart Number
1SNA400772R1300

Pkg

Weightqty(1 pce) g

10222.00Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 19

1SNC161024S0201 - Rev. C1

D95/26 screw clamp terminal blocks
Feed-through - 26 mm 1.024 in spacing

95 mm²0000 AWG

Description–– Closed terminal block: no end section needed, optimized rigidity,–– Use of jumper bars requires the user to cut out the partition.

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161066F0014

Feed-through79.5 3.13"

1SNA400370R2400
1SNA400371R1100
1SNA400791R0000

10
10
10

Mounting instructions

Connecting capacity

D95/2687 3.43"

D95/26
D95/26.N
D95/26.YL

Grey
Blue
Yellow

Main technical data
1 conductor
per clamp

87 3.43"

Closed block withpartition

Weight(1 pce) g
215.00215.00215.00IEC

Rigid: Solid/Stranded
35-120 mm²
Flexible without ferrule35-95 mm²
Flexible with insulated ferrule
Gauge
B12

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

TH 35-7.5,
TH 35-15

2-0000 AWG

2-0000 AWG

Wire stripping
length26 mm
1.02 inTool

Allen keyØ 6 mmØ 0.236 in

232 A / 95 mm² 230 A / 0000 AWG 230 A / 0000 AWG
11400 ATorque1000 V
600 V
600 V
8000 VIP10
NEMA

9 - 9.5 N.m
79.5 - 83.9 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

CSA

Gost R

46 1.81"

26 mm 1.024 in spacing

Accessories
Description

3

2

Color

1
2

End stops
Jumper bars

3

Terminal block
markers

12 mm
0.472 in
2 poles
232 A
3 poles
5 poles
10 polesBlank card

Grey

White

Type
BAZH1
JB26-2
JB26-3
JB26-5
JB26-10
RC810TT
RC1010Part Number
1SNK900102R0000
1SNK926302R0000
1SNK926303R0000
1SNK926305R0000
1SNK926310R0000
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
5
5
5
5
22
1

24.00
41.20
65.70
115.70241.5012
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with D95/26...

Green-yellow

Type
D95/26.PPart Number
1SNA400620R1700

Pkg

Weightqty(1 pce) g

10278.00Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 20

1SNC161025S0201 - Rev. B

1

C2.5/5.P screw clamp terminal blocks
Ground - 5 mm 0.2 in spacing

COMPACT

2.5 mm²
12 AWG

Description–– Screwless DIN rail contact,–– Reliable electrical and mechanical contact with the rail

Ordering details
Description

1SNC161329V0014

GroundColor
Screwless DIN rail connection

Type

Green-yellow

C2.5/5.PIEC

UL - CSA

Rail

0.2 ... 4 mm²
0.2 ... 2.5 mm²
0.2 ... 4 mm²
0.2 ... 2.5 mm²
A3

24 ... 12 AWG

Wire stripping
lengthMain technical data

C2.5/5.P

1SNL605150R0000

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferrule
Gauge

24 ... 12 AWG
24 ... 14 AWG

Tool

49 1.93"41.5 1.63"

50.6 1.99"

Pkg

Weightqty(1 pce) g

100

8.5

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Numbers

Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

12 AWG

Protection

IP20

NEMA 1TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 3.5 mm
Ø 0.14 in

0.5 N.m ± 0.1
4.4 lb.in ± 0.9

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

25.4 1"5 mm 0.2 in spacing

Accessories
1

3

Description

2
1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
9 mm
1
Blank card

0.394 in
0.354 in
0.039

Grey
Grey
White

Type
BAM4
BAZ1
EP5-6
RC510TT
RC510

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNA231600R1500
1SNA231000R0700

Pkg

Weightqty(1 pce) g

50
50
20
22
10

12,00
4.70
1.6
12.00
5.20

1SNC161180S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 21

C2.5/6.P screw clamp terminal blocks
Ground - 6 mm 0.24 in spacing

COMPACT

2.5 mm²
10 AWG

Description–– Screwless DIN rail contact,–– Reliable electrical and mechanical contact with the rail

Ordering details
Description

1SNC161314F0014

GroundColor
Screwless DIN rail connection

Type

Green-yellow

C2.5/6.PIEC

UL - CSA

Rail

0.2 ... 4 mm²
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
0.2 ... 4 mm²
A3

24 ... 10 AWG

Wire stripping
lengthMain technical data

C2.5/6.P

1SNL606151R0000

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferrule
Gauge

24 ... 10 AWG
24 … 12 AWG

Tool

49 1.93"41.5 1.63"

50.6 1.99"

Pkg

Weightqty(1 pce) g

100

10.2

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Numbers

Rated cross section
Rated short-time withstand current (1s)

2.5 mm²
300 A

10 AWG

Protection

IP20

NEMA 1TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 in

0.5 N.m ± 0.1
4.4 lb.in ± 0.9

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

25.4 1"

RoHS

USR

EAC

6 mm 0.24 in spacing

Accessories

3

Description

2
1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
9 mm
1
Blank card

0.394 in
0.354 in
0.039

Grey
Grey
White

Type
BAM4
BAZ1
EP5-6
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
22
10

12,00
4.70
1.6
12
7.50

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC161181S0201 - Rev. A

1

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 22

C4/6.P screw clamp terminal blocks
Ground - 6 mm 0.24 in spacing

COMPACT

Description

4 mm²–– Screwless DIN rail contact,–– Reliable electrical and mechanical contact with the rail

10 AWG

Ordering details
Description

1SNC161314F0014

GroundColor
Screwless DIN rail connection

Type

Green-yellow

C4/6.PIEC

UL - CSA

Rail

0.2 ... 6 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²A424 ... 10 AWG

Wire stripping
lengthMain technical data

C4/6.P

1SNL606150R0000

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferrule
Gauge

24 ... 10 AWG
24 … 12 AWG

Tool

49 1.93"41.5 1.63"

50.6 1.99"

Pkg

Weightqty(1 pce) g

100

10.2

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Numbers

Rated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

10 AWG

Protection

IP20

NEMA 1TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 in

0.65 N.m ± 0.15
5.75 lb.in ± 1.35

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

25.4 1"

RoHS

USR

EAC

6 mm 0.24 in spacing

Accessories
1

3

Description

2
1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
9 mm
1
Blank card

0.394 in
0.354 in
0.039

Grey
Grey
White

Type
BAM4
BAZ1
EP5-6
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
22
10

12,00
4.70
1.6
12
7.50

1SNC161182S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 23

M4/6.3A.P screw clamp terminal blocks
Ground - 6 mm 0.236 in spacing

4 mm²
12 AWG

Description–– Reliable electrical and mechanical contact with the rail,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

1SNC161237F0014

GroundColor
Screw rail connection

Type

Green-yellow

M4/6.3A.P

IEC

UL

Part Number
1SNA195637R1200

Main technical data
Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

Rail

24-12 AWG

Wire stripping
lengthScrew clamp
Tool

M4/6.3A.P

TorqueRated cross section
Rated short-time withstand current (1s)

4 mm²
480 A

12 AWG
Rail connection screw
Tool

56.6 2.23"

54.1 2.13"

50.5 2.00"

49.1 1.93"

Weightqty(1 pce) g

50

22.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg

TorqueG32, TH 35-7.5,
TH 35-15
9.5 mm0.37 inFlat screwdriverØ 4 mmØ 0.16 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.8 N.m
7 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

CSA

Gost R

25 0.98"
30 1.18"

6 mm 0.236 in spacing

Accessories
Description

3

2

1

End stops2
3

End sections
Terminal block
markers

10 mm
0.394 in
9 mm
0.354 in
3 mm
0.118 in
Blank card

Grey
Grey
White

Type
BAM4
BAZ1
FEM3A
RC610TT
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116576R1500
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
22
1

12.00
4.70
3.30
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161005S0201 - Rev. C

1

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 24

M4/6.4A.P screw clamp terminal blocks
Ground - 6 mm 0.236 in spacing

Description

4 mm²–– Reliable electrical and mechanical contact with the rail,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

1SNC161134F0014

GroundColor
Screw rail connection

Type

Green-yellow

M4/6.4A.P

IEC

UL

Part Number
1SNA195638R2300

Main technical data
Connecting capacity
1 conductor
per clamp

Rail
Wire stripping
lengthScrew clamp
Tool

M4/6.4A.P

Torque4 mm²
480 A

Rail connection screw
Tool
Torque50

22.00

G32, TH 35-7.5,
TH 35-15
9.5 mm0.37 inFlat screwdriverØ 4 mmØ 0.16 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in
Flat screwdriverØ 4 mmØ 0.16 in
0.8 N.m
7 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

49.1 1.93"

56.6 2.23"

63.5 2.50"

54.1 2.13"

Weight(1 pce) g

Mounting instructions
CSA

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated cross section
Rated short-time withstand current (1s)

Pkg
qty

CE

RoHS

Gost R

25 0.98"
30 1.18"

6 mm 0.236 in spacing

Accessories
Description
1

3

2

1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
0.394 in
9 mm
0.354 in
3 mm
0.118 in
Blank card

Grey
Grey
White

Type
BAM4
BAZ1
FEM4A
RC610TT
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116629R2200
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
22
1

12.00
4.70
3.80
12
7.50

1SNC161006S0201 - Rev. C

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 25

C6/8.P screw clamp terminal blocks
Ground - 8 mm 0.31 in spacing

COMPACT

Description

6 mm²–– Screwless DIN rail contact,–– Reliable electrical and mechanical contact with the rail.

8 AWG

Ordering details
Description

1SNC161317F0014

GroundColor
Screwless DIN rail connection

Type

Green-yellow

C6/8.PIEC

UL - CSA

Rail

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²A520 ... 8 AWG

Wire stripping
lengthMain technical data

1SNL608150R0000

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferrule
Gauge

20 ... 8 AWG
20 ... 10 AWG

Tool
C6/8.P

Rated cross section
Rated short-time withstand current (1s)

6 mm²
720 A

8 AWG

Protection

IP20

NEMA 1Torque48.3 1.9"

55.5 2.19"
48 1.89"

Pkg

Weightqty(1 pce) g

50

15.2

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Numbers

TH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 4-5 mm
Ø 0.16-0.2 in

0.9 N.m ± 0.1
8 lb.in ± 0.9

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

26.2 1.03"

8 mm 0.31 in spacing

Accessories

3

Description

2
1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
9 mm
2.8
Blank card

0.394 in
0.354 in
0.110

Grey
Grey
White

Type
BAM4
BAZ1
FEM6
RC810TT
RC810

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
20
22
10

12,00
4.70
2.40
12
8.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

1SNC161183S0201 - Rev. A

1

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 26

C10/10.P screw clamp terminal blocks
Ground - 10 mm 0.39 in spacing

COMPACT

Description

10 mm²–– Screwless DIN rail contact,–– Reliable electrical and mechanical contact with the rail

6 AWG

Ordering details
Description

1SNC161320F0014

GroundColor
Screwless DIN rail connection

Type

Green-yellow

C10/10.P

IEC

UL - CSA

Rail

0.5 ... 16 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
0.5 ... 10 mm²
B6

20 ... 6 AWG

Wire stripping
lengthMain technical data

1SNL610150R0000

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferrule
Gauge

20 ... 6 AWG
20 ... 8 AWG

C10/10.P

Tool

48 1.89"

55.5 2.19"

48 1.89"

Pkg

Weightqty(1 pce) g

50

22.5

Mounting instructions

Connecting capacity
1 conductor
per clamp

Part Numbers

Rated cross section
Rated short-time withstand current (1s)

10 mm²1200 A

6 AWG

Protection

IP20

NEMA 1TorqueTH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 5.5-6 mm
Ø 0.22-0.24 in

1.3 N.m ± 0.1
11.5 lb.in ± 0.9

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

23.9 0.94"

10 mm 0.39 in spacing

Accessories
1

3

Description

2
1

End stops2
3

End sections
Terminal block
markers

Color
10 mm
9 mm
2.8
Blank card

0.394 in
0.354 in
0.110

Grey
Grey
White

Type
BAM4
BAZ1
FEM6
RC810TT
RC1010Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
50
20
22
10

12,00
4.70
2.40
12
1.30

1SNC161184S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 27

M16/12.P screw clamp terminal blocks
Ground - 12 mm 0.472 in spacing

16 mm²
4 AWG

Description–– Reliable electrical and mechanical contact with the rail,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description
GroundColor
Screw rail connection

TypePart Number

Green-yellow

M16/12.P

1SNA165130R2300

IEC

UL

CSA

Rail

14-4 AWG

10-6 AWG

Wire stripping
length1SNC161132F0014

Main technical data
Rigid: Solid/Stranded
2.5-25 mm²
Flexible without ferrule
2.5-16 mm²
Flexible with insulated ferrule
Gauge
B7

Screw clamp
Tool

M16/12.P

TorqueRated cross section
Rated short-time withstand current (1s)

16 mm²1920 A

4 AWG

6 AWG
Rail connection screw
Tool
Torque(1 pce) g

20

40.00

G32, TH 35-7.5,
TH 35-15
14 mm
0.55 inFlat screwdriverØ 5.5 mm
Ø 0.22 in
1.2 - 1.4 N.m
10.6 - 12.4 lb.in
Flat screwdriverØ 5.5 mm
Ø 0.22 in
1 N.m
9 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

48 1.89"

55.5 2.18"

49 1.93"

53 2.09"

Weightqty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg

CE

RoHS

USR

CSA

Gost R

22 0.87"
27 1.07"

12 mm 0.472 in spacing

Accessories
Description
1

2

1
2
3

Grey
Grey
White

Type
BAM4
BAZ1
SCFM6
RC810
RC810TT
RC1010Part Number
1SNK900001R0000
1SNK900002R0000
1SNA114825R0500
1SNA234000R0200
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
50
20
10
22
10

12.00
4.70
4.00
8.20
12
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161010S0201 - Rev. C

3

10 mm
0.394 in
9 mm
0.354 inCircuit separators 3 mm
0.118 inTerminal block
Blank card
markers
End stops

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 28

M35/16.P screw clamp terminal blocks
Ground - 16 mm 0.630 in spacing

35 mm²0 AWG

Description–– Reliable electrical and mechanical contact with the rail,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

1SNC161241F0014

GroundColor
Screw rail connection

TypePart Number

Green-yellow

M35/16.P

1SNA165111R1400

IEC

UL

CSA

Rail

8-0 AWG

6-4 AWG

Wire stripping
lengthMain technical data
Rigid: Solid/Stranded
6-50 mm²
Flexible without ferrule
6-35 mm²
Flexible with insulated ferrule
Gauge
B9

Screw clamp
Tool

M35/16.P

TorqueRated cross section
Rated short-time withstand current (1s)

35 mm²4200 A

0 AWG

4 AWG
Rail connection screw
Tool

61.5 2.42"

49 1.93"

Torque20

50.50

G32, TH 35-7.5,
TH 35-15
17 mm
0.67 inFlat screwdriverØ 8 mmØ 0.32 in
2.8 - 3 N.m
24.9 - 26.7 lb.in
Flat screwdriverØ 5.5 mm
Ø 0.22 in
2.8 - 3 N.m
24.9 - 26.7 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
54 2.13"59 2.32"

Weight(1 pce) g

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

CE

RoHS

USR

CSA

Gost R

22 0.87"
27 1.07"

16 mm 0.630 in spacing

Accessories
Description
1

2

1

End stops2

Terminal block
markers

Color
10 mm
0.394 in
9 mm
0.354 in
Blank card

Grey
White

Type
BAM4
BAZ1
RC810
RC810TT
RC1010Part Number
1SNK900001R0000
1SNK900002R0000
1SNA234000R0200
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
50
10
22
10

12.00
4.70
8.20
12
1.30

1SNC161011S0201 - Rev. C

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 29

D70/22.P screw clamp terminal blocks
Ground - 22 mm 0.866 in spacing

70 mm²00 AWG

Description
Reliable electrical and mechanical contact with the rail.

Ordering details
Description

1SNC161070F0014

GroundColor
Screw rail connection

TypePart Number
1SNA400772R1300(1 pce) g

10222.00D70/22.P

IEC

UL

CSA

Rail

TH 35-15

4-00 AWG

4-00 AWG

Wire stripping
length25 mm
0.984 inScrew clamp
Tool

Allen keyØ 6 mmØ 0.236 in
6 - 7 N.m
53.4 - 62.3 lb.in
Allen keyØ 4 mmØ 0.158 in
1.8 - 2 N.m
15.9 - 17.7 lb.in

Mounting instructions

Connecting capacity

Rigid: Solid/Stranded
16-95 mm²
Flexible without ferrule
16-70 mm²
Flexible with insulated ferrule
Gauge
B11

TorqueD70/22.P

Weightqty

Green-yellow

Main technical data
1 conductor
per clamp

Pkg

Rated cross section
Rated short-time withstand current (1s)

70 mm²8400 A

00 AWG
8088 A

00 AWG
8088 A

Rail connection screw
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR CNR

CSA

Gost R

22 mm 0.866 in spacing

Accessories
Description
2

1
2

End stops
Terminal block
markers

12 mm
0.472 in
Blank card

Grey
White

Type
BAZH1
RC810TT
RC1010Part Number
1SNK900102R0000
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
22
1

24.00
12
1.30

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161012S0201 - Rev. D

1

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 30

D95/26.P screw clamp terminal blocks
Ground - 26 mm 1.024 in spacing

95 mm²0000 AWG

Description
Reliable electrical and mechanical contact with the rail.

Ordering details
Description

1SNC161068F0014

GroundColor
Screw rail connection

TypePart Number
1SNA400620R1700

Weight(1 pce) g

10278.00

Green-yellow

D95/26.P

IEC

UL

CSA

Rail

TH 35-15

2-0000 AWG

2-0000 AWG

Wire stripping
length26 mm
1.023 inScrew clamp
Tool

Allen keyØ 6 mmØ 0.236 in
9 - 9.5 N.m
79.5 - 83.9 lb.in
Allen keyØ 4 mmØ 0.158 in
1.8 - 2 N.m
15.9 - 17.7 lb.in

Main technical data

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg
qty

Rigid: Solid/Stranded
35-120 mm²
Flexible without ferrule35-95 mm²
Flexible with insulated ferrule
Gauge
B12

D95/26.P

Torque95 mm²11400 A

0000 AWG
12840 A

0000 AWG
12840 A

26 1.02"

Rated cross section
Rated short-time withstand current (1s)Rail connection screw
Tool
Torque87 3.43"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
RoHS

USR CNR

CSA

Gost R

87 3.43"

CE

46 1.81"

26 mm 1.024 in spacing

Accessories
Description
1

2

1
2

End stops
Terminal block
markers

Color
12 mm
0.472 in
Blank card

Grey
White

Type
BAZH1
RC810TT
RC1010Part Number
1SNK900102R0000
1SNA234600R1000
1SNA238000R1600

Pkg

Weightqty(1 pce) g

50
22
1

24.00
12
1.30

1SNC161013S0201 - Rev. D

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 31

MA2.5/5.D2 screw clamp terminal blocks
Double deck - 5 mm 0.197 in spacing

2.5 mm²
12 AWG

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 5 mm 0.197 in spacing,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

1SNC161117F0014

Feed-through67 2.64"64.5 2.54"

Grey
Blue
Beige

Part Number

MA2.5/5.D2
MA2.5/5.D2.N
MA2.5/5.D2

1SNA115490R1300
1SNA125490R1500
1SNA195490R1400

Pkg

Weightqty(1 pce) g

50
50
50

15.00
15.00
15.00

Mounting instructions

Connecting capacity

MA2.5/5.D2

59.5 2.34"

2 feed-through circuits

Type

Main technical data
1 conductor
per clamp

65.5 2.57"

Color

IEC

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

20-12 AWG

Wire stripping
length9 mm
0.354 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

24 A / 2.5 mm² 20 A / 12 AWG 25 A / 12 AWG
300 A
Torque
630 V
300 V
300 V
8000 V
IP20
NEMA 1

0.4 - 0.6 N.m
3.5 - 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

CSA

Gost R

33 1.30"
38 1.50"5 mm 0.197 in spacing

Accessories
Description
1

2

3

4

5

6

1
2
3

4

7

8

5
6
7
8
9

Color

12 mm
0.472 in
1 mm
0.039 in
2 poles
24 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 2 poles
30 A
10 polesInsulating tips
For lateral jumper bars type PC...
Circuit separators 0 mm
0 in
Shield connectors
Inner deck jumper bars
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

Grey
Grey

Grey

Grey

White

Type
BAZH1
FEM6D
BJMI5D-2
BJMI5D-3
BJMI5D-4
BJMI5D-5
BJMI5D-10
PC5-2
PC5-10EIP
SCMA5DCBM5D
ITV5RC510TT
RC510

Part Number
1SNK900102R0000
1SNA118499R2300
1SNA176736R2100
1SNA176737R2200
1SNA176738R0300
1SNA176739R0400
1SNA176740R1100
1SNA113542R1000
1SNA113544R1200
1SNA113550R2400
1SNA116720R2100
1SNA173530R2400
1SNA176259R1300
1SNA231600R1500
1SNA231000R0700

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
10
50
20
22
10

24.00
2.70
2.00
3.00
4.00
6.00
12.00
1.80
6.00

2.00
12.00
5.20
1SNC161033S0201 - Rev. C

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

9Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 32

MA 2.5/5.D1.1 screw clamp terminal blocks
Double deck - 5 mm 0.197 in spacing

2.5 mm²

With vertical interconnection and partition

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

Feed-through1 Feed-through circuitwith vertical interconnection and partition

Main technical data
Rated voltage
Impulse withstand voltage
Protection
5 mm 0.197 in spacing

CE

RoHS

Grey

IEC
630 V
8000 V
IP20
CSA

MA2.5/5.D1.1

UL

1SNA115530R1200

CSA
300 V

50

Weight(1 pce) g
15.00

Nota

NEMA 1Gost R

Accessories
1

Description

2

Color

Type

Part Number

Pkg
qty

Test sockets
Test plugs

DIA 2 mm 0.079 in
DIA 2 mm 0.079 in

Black

AL2
FC2

1SNA164950R0000
1SNA007865R2600

50
100

1SNC161099S0201 - Rev. B

1
2

Weight(1 pce) g

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 33

M4/6.D2 screw clamp terminal blocks
Double deck - 6 mm 0.236 in spacing

4 mm²
12 AWG

Description–– Save space with double deck terminal blocks: 2 independent circuits connected in just 6 mm 0.236 in spacing,–– Flexibility: snap onto symmetrical and asymmetrical rails.

Ordering details
Description

Color

Feed-through 2 feed-through circuits
1SNC161112F0014

Grey
Blue
OrangeYellow
Green
Red
White
Black
Beige

Type

Part Number

M4/6.D2
M4/6.D2.N
M4/6.D2
M4/6.D2
M4/6.D2
M4/6.D2
M4/6.D2
M4/6.D2
M4/6.D2

1SNA115271R2200
1SNA125271R2400
1SNA105049R0600
1SNA105045R2200
1SNA105044R2100
1SNA105048R0500
1SNA105046R2300
1SNA105047R2400
1SNA195271R2300

Main technical data

M4/6.D2

33 1.30"
38 1.50"

67 2.64"59.5 2.34"

64.5 2.54"

65.5 2.57"

Weightqty(1 pce) g

50
50
50
50
50
50
50
50
50

20.00
20.00
20.00
20.00
20.00
20.00
20.00
20.00
20.00

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg

IEC

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule 0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

32 A / 4 mm²
480 A
800 V
8000 V
IP20

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

24-10 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

20 A / 12 AWG 25 A / 10 AWG
300 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

6 mm 0.236 in spacing

CE

RoHS

USR

CSA

Gost R

Accessories
Description
1

2

3

4

5

6

1
2
3

4
5
6
7
8

8

12 mm
0.472 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inCircuit separators
1 mm
0.039 inShield connectors
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

Grey
Grey

Grey

White

Type
BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10
EL6
SCM6D
SCF6D
CBM5D
RC610TT
RC610

Part Number
1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA113482R0500
1SNA118495R1700
1SNA173530R2400
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
10
20
50
22
1

24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
0.30
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.
1SNC161028S0201 - Rev. C

7

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 34

M4/6.D1 screw clamp terminal blocks
Double deck - 6 mm 0.236 in spacing

4 mm²

With vertical interconnection and partition

10 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

Feed-through1 feed-through circuitwith vertical interconnection and partition

Main technical data
Rated voltage
Impulse withstand voltage
Protection
6 mm 0.236 in spacing

CE

RoHS

Grey
Blue

IEC
800 V
8000 V
IP20
CSA

M4/6.D1
M4/6.D1.N
UL

1SNA115166R1100
1SNA125166R1300
CSA
600 V

50
50

Weight(1 pce) g
20.00
20.00

Nota

NEMA 1Gost R

Accessories
Description

2
1

Test sockets

2

Test plugs

Color
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
DIA 2 mm 0.079 in

Black

Type
AL2
AL3
FC2

Part Number
1SNA163070R0000
1SNA163261R0000
1SNA007865R2600

Pkg

Weightqty(1 pce) g

50
50
100

1.20

1SNC161101S0201 - Rev. B

1

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 35

M4/6.DD screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing

4 mm²
12 AWG

Description
Protect or test your circuit with one 1N4007 diodes.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161208F0014

Component
holder

67 2.64"

1SNA115168R2300

50

Mounting instructions
IEC

M4/6.DD

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

18-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

20 A / 4 mm²
480 A
500 V

25 A / 12 AWG 25 A / 12 AWG

IP20NEMA 1

600 V

150 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
59.5 2.34"

64.5 2.54"

M4/6.DD

Grey

Main technical data
1 conductor
per clamp

65.5 2.58"

Cathode of the blocking
diode connected to thelower circuit

Weight(1 pce) g
20.00

CE

RoHS

USR

CSA

Gost R

33 1.30"

Typical lamp test application

38 1.50"

6 mm 0.236 in spacing

PC61-10

Description
1

2

3

4

5

6

Color

Type

Part Number

Pkg
pce

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block
Blank card
markers
End stops
End sections
Jumper bars

Dark grey
Grey

White

BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610TT
RC610

1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233600R1700
1SNA233000R0100

20
20
10
10
10
10
10
10
10
22
1

Weight(1 pce) g
24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 36

1SNC161133S0201 - Rev. B

Accessories

M4/6.DD1 screw clamp terminal blocks
Component holder - 6 mm 0.236 in spacing

4 mm²
12 AWG

Description
Protect or test your circuit with one 1N4007 diodes.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161208F0014

Component
holder

67 2.64"

M4/6.DD1

1SNA115184R0400

50

Mounting instructions
IEC

M4/6.DD

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

18-12 AWG

Wire stripping
length

8.5 mm0.33 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 Nm
4.4 - 5.3 lb.in

20 A / 4 mm²
480 A
500 V

25 A / 12 AWG 25 A / 12 AWG
600 V

IP20

NEMA 1

150 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
59.5 2.34"

64.5 2.54"

Grey

Main technical data
1 conductor
per clamp

65.5 2.58"

Cathode of the blocking
diode connected to theupper circuit

Weight(1 pce) g
20.00

CE

RoHS

USR

CSA

Gost R

33 1.30"

Typical lamp test application

38 1.50"

6 mm 0.236 in spacing

PC61-10
Description
1

2

3

4

5

6

Color

Type

Part Number

Pkg
pce

1
2
3

4
5
6

10 mm
0.394 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block
Blank card
markers
End stops
End sections
Jumper bars

Dark grey
Grey

White

BAZH1
FEM6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6RC610TT
RC610

1SNK900102R0000
1SNA118499R2300
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA233600R1700
1SNA233000R0100

20
20
10
10
10
10
10
10
10
22
1

Weight(1 pce) g
24.00
2.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 37

1SNC161135S0201 - Rev. B

Accessories

M6/8.D2 screw clamp terminal blocks
Double deck - 8 mm 0.315 in spacing

Description

6 mm²–– Save space with double deck terminal blocks: 2 independent circuits,–– Flexibility: snap onto symmetrical and asymmetrical rails.

8 AWG

Ordering details
Description

1SNC161119F0014

Feed-throughColor
2 feed-through circuits

Type
Grey
Beige

Part Number

M6/8.D2
M6/8.D2

1SNA115501R1200
1SNA195501R1300

Main technical data
IEC

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

81 3.19"

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

50
50

33.00
33.00

CSA

Rail

G32, TH 35-7.5,
TH 35-15

18-8 AWG

8 AWG

Wire stripping
length

12 mm
0.47 inTool

Flat screwdriverØ 4 - 5 mm
Ø 0.157 - 0.197 in

41 A / 6 mm²
720 A
800 V
8000 V
IP20

Torque0.8 - 1 N.m
7.1 - 8.9 lb.in

50 A / 8 AWG

45 A / 8 AWG

600 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

73.5 2.89"

78.5 3.09"(1 pce) g

UL

M6/8.D

88 3.38"

Weightqty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg

CE

RoHS

USR

CSA

Gost R

46 1.81"
51 2.00"

8 mm 0.315 in spacing

Accessories
Description

3

5

2

1
2
3

4
4
5

12 mm
1 mm
2 poles
3 poles
4 poles
5 poles
10 polesCircuit separators 0 mm
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

0.472 in
0.039 in
41 A

0 in

Grey
Grey

Grey
White

Type
BAZH1
FEM8D1
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-5
BJMI8-10
SCM6RC810TT
RC810

Part Number
1SNK900102R0000
1SNA116656R2500
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176672R0100
1SNA176673R0200
1SNA113003R1000
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
22
1

24.00
10.00
4.50
6.00
10.00
12.22
20.00
0.30
12
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161043S0201 - Rev. C

1

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 38

M6/8.D1 screw clamp terminal blocks
Double deck - 8 mm 0.315 in spacing

6 mm²With vertical interconnection and partition

8 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

Feed-through1 feed-through circuitwith vertical interconnection and partition

Main technical data
Rated voltage
Impulse withstand voltage
Protection
CE

8 mm 0.315 in spacing

RoHS

Grey

IEC
800 V
8000 V
IP20
USR

CSA

CSA
600 V

50

Nota

NEMA 1

Accessories
1

Test sockets

2

Test plugs

Color
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
DIA 2 mm 0.079 in
DIA 4 mm 0.157 in

Black
White

Type
AL2
AL3
FC2
FC4

Part Number
1SNA163043R2100
1SNA163261R0000
1SNA007865R2600
1SNA167860R0100

Pkg

Weightqty(1 pce) g

50
50
100
10

0.90
1.20

1SNC161102S0201 - Rev. B

2

UL
600 V

1SNA115498R1700

Gost R

Description

1

M6/8.D1

Weight(1 pce) g
36.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 39

D4/6.T3 screw clamp terminal blocks
Triple deck - 6 mm 0.236 in spacing

Description

4 mm²

Save space with triple deck terminal blocks: 3 independent circuits connected in just 6 mm 0.236 in spacing;–– closed terminal block: no end section needed, better rigidity.

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161072F0014

Feed-through3 feed-through circuits

D4/6.T3

Grey

1SNA299683R0100

Main technical data
Connecting capacity
1 conductor
per clamp

Mounting instructions
IEC

UL

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge
A4

CSA

22-12 AWG

Rail
Wire stripping
lengthFlat screwdriverØ 4 mmØ 0.16 inTorque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

20 A / 12 AWG
300 V
NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. for more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

72 2.83"

79.5 3.13"

90 3.54"

32 A / 4 mm²
480 A
500 V
6000 V
IP20

G32, TH 35-7.5,
TH 35-15
9.5 mm0.37 in

Tool
D4/6.T

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

25

Weight(1 pce) g
27.00

RoHS

USR CNR

Gost R

43.4 1.70"

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

1
2

3
4
5
6
7

Color

12 mm
0.472 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Circuit separators 1.5 mm
0.059 in
Test sockets
DIA 2 mm 0.079 in
Test plugs
DIA 2 mm 0.079 in
Terminal block markers Blank card
End stops
Jumper bars

Grey

White
Black
White

Type
BAZH1
BJM62

PC61-10
SCD
AL2
FC2
RC65

Part Number
1SNK900102R0000
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173221R2200
1SNA173226R2700
1SNA163311R2200
1SNA103189R2600
1SNA167319R0600
1SNA007865R2600
1SNA232000R0000

Pkg

Weightqty(1 pce) g

50
10
10
10
10
10
10
10
50
100
1

24.00
2.00
3.00
4.00
5.00
10.00
5.00
1.00

Pkg

Weight(1 pce) g
30.00

3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

7

With ground, 3 feed-through circuit
Description

Color

Type

Part Number

qty

Feed-through + 3 feed-through circuits+ 1 groundgroundGrey,
Green-Yellow

D4/6.T3.P

1SNA299684R0200

25

6 mm 0.236 in spacing
Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 40

1SNC161026S0201 - Rev. C

Ordering details

D4/6.T1 screw clamp terminal blocks
Triple deck - 6 mm 0.236 in spacing

4 mm²

1 feed-through circuit

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

Feed-through1 feed-through circuit

1

D4/6.T1

Main technical data

IEC

UL

Rated voltage
Impulse withstand voltage
Protection

500 V
6000 V
IP20

300 V

CE

6 mm 0.236 in spacing

Black

RoHS

USR CNR

1SNA199219R0300
CSA

25

Weight(1 pce) g
29.00

Can not be fitted with accessories: test sockets, test
plugs and jumper bars BJM62

NEMA 1Gost R

Accessories
Description1

Jumper bars

Color
1 poles

24 A

Grey

Type
AD2.5

Part Number

Pkg

Weightqty(1 pce) g

1SNA114205R2000

50

1.60

Part Number

Pkg

Ground screw clamp terminal blocks
Description

Color

Type

qty

Green-yellow

D4/6.P.T1

Main technical data

IEC

UL

Rated voltage
Impulse withstand voltage
Protection
Rated short-time withstand current (1s)500 V
6000 V
IP20
480 A

300 V

Profile aligned with D4/6.T3...

1SNA199220R0000
CSA

25

Can not be fitted with accessories: test sockets,
test plugs and jumper bars BJM62

NEMA 1

1SNC161103S0201 - Rev. C

GroundWeight(1 pce) g

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 41

MA2.5/5.SNB screw clamp terminal blocks
Disconnect with blade - 5 mm 0.197 in spacing

2.5 mm²
12 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with screwdriver,–– Same profile as MA2.5/5 feed-through terminal block for aligned marking and identical end section use.

Ordering details
Description

Color

1SNC161085F0014

Disconnect

TypePart Number

Grey-orange

MA2.5/5.SNB

IEC

UL

1SNA115699R2000

Main technical data
Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-2.5 mm²
Flexible with insulated ferrule
Gauge
A3

10 A / 2.5 mm²
120 A
320 V
4000 V
IP20
NEMA 1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
57 2.24"
59.5
2.34"

68.5 2.69"

50

8.00

Rail

G32, TH 35-7.5,
TH 35-15

28-12 AWG

Wire stripping
length10 mm
0.39 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

Torque0.4 - 0.6 N.m
3.5 - 5.3 lb.in

15 A / 12 AWG
600 V

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
C

CE

RoHS

US

cCSAusGost R

52
2.05"

66 2.59"

61 2.40"(1 pce) g

CSA

MA2.5/5.SNB

44.5 1.75"

Weightqty

Mounting instructions

Connecting capacity
1 conductor
per clamp

Pkg

18 0.71"
23 0.91"

5 mm 0.197 in spacing

Accessories
Description
1

2

1
2
3

5

4

6

4
5
6

0.394 in
0.354 in
0.110 in
30 A

Grey

0.118 in

Grey

Shield connectors
Terminal block
Blank card
markers

Grey
Grey

White

Type
BAM4
BAZ1
FEM6
PC5-2
PC5-10
SCFM6
SCF6
CBM5
RC510TT
RC510

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA118368R1600
1SNA113542R1000
1SNA113544R1200
1SNA114825R0500
1SNA118707R0300
1SNA178745R1400
1SNA231600R1500
1SNA231000R0700

Pkg

Weightqty(1 pce) g

50
50
20
10
10
20
20
50
22
1

12.00
4.70
2.40
1.80
6.00
4.00
12.00
5.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161017S0201 - Rev. C

3

10 mm
9 mm
End sections
2.8 mmLateral jumper bars 2 poles
10 polesCircuit separators 3 mm
End stops

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 42

C4/6.S screw clamp terminal blocks

Disconnect with blade - 6 mm 0.24 in spacing

Description

4 mm²–– Ease your disconnect operationswith the disconnect blade operated by hand or with a screwdriver,–– Same profile as C2.5/5 or C4/6 feed through terminal block for aligned marking and wiring.

10 AWG

Ordering details
Description

1SNC161333V0014

Disconnect

Color
Profile aligned with C2.5/5 and C4/6
feed through and ground73 2.87"

65.5 2.58"

48 1.89"

55.5 2.19"

43.6 1.72"

Grey

C4/6.S

Main technical data

Part Numbers
1SNL606310R0000

Pkg

Weightqty(1 pce) g

100

8.7

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section

0.2 ... 6 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²A4
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
24 A / 2.5 mm²

24 ... 10 AWG

Wire stripping
lengthRated short-time withstand current (1s)

300 A

Rated voltage
Impulse withstand voltage
Protection

400 V
6000 V
IP20

1 conductor
per clamp

C4/6.SType

24 ... 10 AWG
24 … 12 AWG
24 ... 14 AWG

Tool

24 ... 16 AWG
25 A / 10 AWG
TorqueTH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 in

0.65 N.m ± 0.15
5.75 lb.in ± 1.35

300 V
NEMA 1

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

17.5 0.69"

6 mm 0.24 in spacing

Accessories
1

Description

2
1

3

4

2
3

4

10 mm
9 mm
End sections
1
Lateral jumper bars 2 poles
3 poles
4 poles
10 poles25 poles
50 polesTerminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.039
35 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
24 (IEC)
24 (IEC)

Grey
Grey
Grey

Black
White

Type
BAM4
BAZ1
EP5-6
PC6-2
PC6-3
PC6-4
PC6-10LJB6-25E
LJB6-50
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNL906751R0000
1SNL906750R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
22
10

12,00
4.70
1.6
2.00
2.00
3.00
8.00
17.5
25.5
12
7.50

1SNC161185S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 43

M4/6.SNB screw clamp terminal blocks
Disconnect with blade - 6 mm 0.236 in spacing

4 mm²
10 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with screwdriver,–– Same profile as M4/6 feed-through terminal block for aligned marking.

Ordering details
Description

Color

1SNC161078F0014

Disconnect

M4/6.SNB

57 2.24"
59.5
2.34"

68.5 2.69"

52
2.05"

66 2.59"

1SNA115986R0000
1SNA105053R2200
1SNA115686R1300
1SNA195686R1400

Pkg

Weightqty(1 pce) g

50
50
50
50

11.00
11.00
11.00
11.00

M4/6.SNB
M4/6.SNB
M4/6.SNB
M4/6.SNB

IEC

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-10 AWG

24-10 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.16 inTorque0.5 - 0.6 N.m
4.4 - 5.3 lb.in

Main technical data
1 conductor
per clamp

61 2.40"

Part Number

Grey, Orange
Orange, Orange
Grey, Grey
Beige, Grey

Mounting instructions

Connecting capacity

44.5 1.75"

Type

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

20 A / 4 mm²
300 A
400 V
4000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

10 A / 10 AWG 15 A / 10 AWG
300 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
C

CE

RoHS

USR

US

cCSAusGost R

18 0.71"
23 0.91"

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

4

6

1
2
3
4
5
6
7

10 mm
9 mm
End sections
3 mm
Jumper bars
1 poles
Lateral jumper bars 10 poles
Circuit separators 3 mm
Shield connectors
Terminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.118 in
24 A
35 A
0.118 in

Grey
Grey
Grey
Grey
White

Type
BAM4
BAZ1
FEM62
AD2.5
PC61-10SCFM6
CBM5RC610TT
RC610

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA114994R0700
1SNA114205R2000
1SNA163311R2200
1SNA114825R0500
1SNA178745R1400
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
50
10
20
50
22
1

12.00
4.70
2.40
1.60
5.00
4.00
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161057S0201 - Rev. C

7

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 44

M6/8.SNB screw clamp terminal blocks
Disconnect with blade - 8 mm 0.315 in spacing

6 mm²
8 AWG

Description–– Ease your disconnect operations with the disconnect blade operated by hand or with screwdriver,–– Same profile as M6/8 feed-through terminal block for aligned marking.

Ordering details
Description

Color

1SNC161084F0014

Disconnect

TypePart Number
1SNA115688R2500
1SNA105055R2400

19.00
19.00

IEC

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-8 AWG

22-8 AWG

Wire stripping
length

12 mm
0.47 inTool

Flat screwdriverØ 4-5 mm
Ø 0.16-0.20 in

Torque0.8 - 1 N.m
7.1 - 8.9 lb.in

Mounting instructions

Connecting capacity

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule 0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

15 A / 6 mm²
180 A
400 V
4000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection
57 2.24"
59.5
2.34"

72 2.83"

20 A / 8 AWG

20 A / 8 AWG

300 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
C

52
2.05"

69.5 2.73"

64.5 2.54"

50
50

M6/8.SNB
M6/8.SNB

M6/8.SNB

47 1.85"

Weight(1 pce) g

Grey, Grey
Orange, Orange

Main technical data
1 conductor
per clamp

Pkg
qty

CE

RoHS

USR

US

cCSAusGost R

20.5 0.81"
25.5 1.04"

8 mm 0.315 in spacing

Accessories
Description
1

2

3

4

5

6

2
3
4

5
6
7

10 mm
0.394 in
9 mm
0.354 inEnd sections
3 mm
0.118 inJumper bars
1 poles
24 A
Lateral jumper bars 2 poles
50 A
3 poles
4 poles
10 polesCircuit separators 3 mm
0.118 in
Test plugs
DIA 2 mm 0.079 in
Terminal block
Blank card
markers
End stops

Grey
Grey
Grey

Grey
Black
White

Type
BAM4
BAZ1
FEM8
AD2.5
PC8-2
PC8-3
PC8-4
PC8-10SCFM6
FC2
RC810TT
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA113373R2600
1SNA114205R2000
1SNA116538R1700
1SNA116539R1000
1SNA116540R2500
1SNA163313R2400
1SNA114825R0500
1SNA007865R2600
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
20
50
10
10
10
10
20
100
22
1

12.00
4.70
3.00
1.60
3.00
4.00
6.00
4.00
12
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161059S0201 - Rev. C

7

1

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 45

M4/6.D2.SNBT screw clamp terminal blocks

Disconnect with blade - with test socket - 6 mm 0.236 in spacing

Description

4 mm²–– Save space with double deck terminal blocks: 1 disconnect circuit on top + 1 independent feed-throughcircuit on bottom in just 6 mm 0.236 in spacing,–– Ease your disconnect operations with the disconnect blade operated by hand or with screwdriver,–– Same profile as M4/6.D2 feed-through terminal block for aligned marking and identical end section use.

12 AWG

Ordering details
1SNC161089F0014

Description
Disconnect

Color
With 4 tests sockets
DIA 2 mm 0.079 in

Grey

Part Number

M4/6.D2.SNBT

1SNA115561R1500

Main technical data
1 conductor
per clamp

IEC70 2.76"
72.5
2.85"

85.5 3.37"

65
2.56"

83 3.27"

Weightqty(1 pce) g

50

21.00

Rigid: Solid/Stranded
0.5-4 mm²
Flexible without ferrule 0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

24-12 AWG

24-10 AWG

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.6 N.m
4.4 - 5.3 lb.in

81 3.19"

78 3.07"

Pkg

Mounting instructions

Connecting capacity

M4/6.D2.SNBT

Type

10 A / 4 mm²
120 A
400 V
4000 V
IP20

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

20 A / 12 AWG 15 A / 10 AWG
300 V

600 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. for more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

32.5 1.28"

CCE

38 1.50"RoHSUSR CNRUS

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

2

3

4

5

6

4
5
6
7

12 mm
0.472 in
1 mm
0.039 in
2 poles
32 A
3 poles
4 poles
5 poles
10 poles
Lateral jumper bars 10 poles
35 A
Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
Test plugs
DIA 2 mm 0.079 in
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

Grey
Grey
Grey

Black
White

Type
BAZH1
FEMS6D
BJMI6D-2
BJMI6D-3
BJMI6D-4
BJMI6D-5
BJMI6D-10
PC61-10EL6FC2RC610TT
RC610

Part Number
1SNK900102R0000
1SNA116591R0500
1SNA179668R2000
1SNA179669R2100
1SNA179670R2600
1SNA179671R1300
1SNA179672R1400
1SNA163311R2200
1SNA173627R2100
1SNA007865R2600
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
20
10
10
10
10
10
10
10
100
22
1

24.00
3.70
4.00
6.00
8.00
10.00
20.00
5.00
0.10
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161094S0201 - Rev. C

7

1
2
3

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 46

SNACompact Terminal blocks
Test and Measurement

SECURE YOUR MEASUREMENTOPERATIONSThe C6/8.ST... test and measurement terminal block benefit fromour long experience in the energy applications and from
SNACompact features: Compact, performance, common
accessories and marking.

CONVENIENT AND SECURED DESIGN• Secured sliding link operated with screwdriver

SHORT-CIRCUIT CT CIRCUITS SAFELY ANDCONVENIENTLY• Sliding link status – open or close symbols help
to visualize the position

Add the short-circuit bridges accessory (SCB-ST)
for your CT's (Current Transformer) application.

• Two built-in test sockets for DIA 4 mm test plug.

• Operated by screwdriver• Short-circuited position secured by screws Insulated.

GUARANTEE ACCESS ONLY TO AUTHORIZEDOPERATORS

Add the insulated test socket accessory (STI4-Y)
for safe measurement.

Compatible with SNK accessories (KCO and CO)
to prevent wrong use.

• Compatible with IP20 test plug DIA 4 mm (IEC 60010-031).

• Cover can be sealed with a cable tie or a seal.

1SNC160232S0201 - Rev. A

SAFE MEASUREMENT WITH INSULATED TEST
SOCKET

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 47

SNACompact series, terminal blocks
Typical schematics for measuring devices

CT's
P1

L1
P1

L2
L3

PT's

P1
S1

P2 S1

P2 S1

P2
S2

S2

S2

P

P

P

S

S

S

1

2

3

N

N

Current inputs

Voltage inputs
Measuring devices(ie: meters, protection relays…)

From a basic configuration with disconnect
terminal blocks, short-circuit bridges and end sections.

CT's

To an IP20 and convenient configuration with the addition of
Insulated test sockets, the protecting cover kits and the cover.

PT's

CT's

(Current tranformers) (Potential transformers)

PT's(Current tranformers) (Potential transformers)

2
7

5
1

1

C6/8.ST1

2

SCB-ST

3

EP8-ST

6

4

C6/8.STI1.IP20

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

45

SCB-ST-2P

6

KCO

7

1SNC160233S0201 - Rev. A

3

COPAGE 48

C6/8.ST1 screw clamp terminal blocks

Disconnect with sliding link - 8 mm 0.31 in spacing

Description

6 mm²–– Secure your disconnect operations in control circuits with the sliding link operated with a screwdriver,–– Includes two built-in test sockets compatible with Dia 4mm 0.157 in test plugs,–– Convenient short-circuit operations with the accessory SCB-ST.

8 AWG

1SNC161332V0014

Ordering details
Description
Disconnect

Color
Two built-in test sockets compatible
with Dia 4mm 0.157 in test plugs

50.7 2"

58.2 2.29"

72 2.83"

Grey

C6/8.ST1

Main technical data

Part Numbers
1SNL608310R0000

Pkg

Weightqty(1 pce) g

25

21.4

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²A5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
40 A / 6 mm²
720 A

20 ... 8 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 VIP20

300 V

1 conductor
per clamp

C6/8.ST1Type

20 ... 8 AWG
20 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 14 AWG
37 A / 8 AWG

TorqueDisconnect device
Tool
TorqueNEMA 1
Test socketTool

36 1.42"8 mm 0.31 in spacing

TorqueTH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 4-5 mm
Ø 0.16-0.2 in
0.9 N.m ± 0.1
8 lb.in ± 0.9
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 ... 0.6 N.m
3.5 ... 5.3 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 ... 0.6 N.m
3.5 ... 5.3 lb.in

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

1

Description

2
1

3

4

5

6

7

8

9

10

10 mm
0.394 in
9 mm
0.354 in2 End sections
1
0.039
3 Jumper bars
10 poles
4 Lateral jumper bars 2 poles
50 (IEC)
10 poles50 (IEC)
4/6 poles
50 (IEC)
4/8 poles
50 (IEC)
4/10 poles 50 (IEC)
3/4 poles
50 (IEC)
4/6 poles
50 (IEC)
4/8 poles
50 (IEC)
2/3 poles
50 (IEC)
4/7 poles
50 (IEC)
5 Test sockets
DIA 4 mm 0.157 in IP20
6 Test plugs
DIA 4 mm 0.157 in
DIA 4 mm 0.157 in IP20
7 Protecting cover kits
8 Protecting covers 1 m 39.4 in length
9 Short circuit
2 polesbridges
10 Terminal block
Blank card
markers
End stops

Color

Type

Grey
Grey
Black

Yellow
White
Red
Dark grey
Transparent
Yellow
White

BAM4
BAZ1
EP8-STJB-ST-10P
PC8-2
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4
PC8-R7PC8-R8PC8-R6
PC8-R5
STI4-YL
FC4
FC4-1
KCO
CO
SCB-ST-2P
SCB-kit
RC810TT
RC810

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900102R0000
1SNL908310R0000
1SNA116538R1700
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA400849R0000
1SNA400850R0000
1SNA400843R0000
1SNA400842R0000
1SNL900201R0000
1SNA167860R0100
1SNA167927R1000
1SNK900624R0000
1SNK900604R0000
1SNL900602R0000
1SNL900902R0000
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
10
10
10
10
10
10
10
10
10
10
10
10
25
10
10
1
1
25
25
22
10

12,00
4.70
3.35
4.03
3.00
14.00
6.60
7.80
9.00
4.50
6.60
7.80
6.60
6.60
6.76
10.00
11.00
47.80
300.00
2.71
4.81
12
8.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.
Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 49

1SNC161189S0201 - Rev. A

Accessories

C6/8.ST1.IP20 screw clamp terminal blocks
Disconnect with sliding link - 8 mm 0.31 in spacing

Description

6 mm²–– Secure your disconnect operations in control circuits with the sliding link operated with a screwdriver,–– Includes two built-in test insulated test sockets compatible with IP20 Dia 4mm 0.157 in test plugs,–– Convenient short-circuit operations with the accessory SCB-ST.

8 AWG

Ordering details
1SNC161336V0014

Description
DisconnectColor
Two insulated test sockets
compatible with IP20 Dia 4mm
0.157 in test plugs

Grey

62 2.44"69.5 2.74"

72 2.83"

C6/8.ST1.IP20

Main technical data

Part Numbers
1SNL608311R0000

Pkg

Weightqty(1 pce) g

25

35

Mounting instructions

Connecting capacity

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section
Rated short-time withstand current (1s)

0.5 ... 10 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²
0.5 ... 6 mm²A5
0.5 ... 4 mm²
0.5 ... 4 mm²
0.5 ... 4 mm²
40 A / 6 mm²
720 A

20 ... 8 AWG

Wire stripping
lengthRated voltage
Impulse withstand voltage
Protection

630 V
8000 VIP20

300 V

1 conductor
per clamp

C6/8.ST1.IP20

Type

20 ... 8 AWG
20 ... 10 AWG
20 ... 12 AWG

Screw clamp
Tool

20 ... 14 AWG
37 A / 8 AWG

TorqueDisconnect device
Tool
TorqueNEMA 1
Test socketTool

36 1.42"Torque8 mm 0.31 in spacing

TH 35-7.5,
TH 35-15
12 mm
0.47 inFlat screwdriverØ 4-5 mm
Ø 0.16-0.2 in
0.9 N.m ± 0.1
8 lb.in ± 0.9
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 ... 0.6 N.m
3.5 ... 5.3 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 ... 0.6 N.m
3.5 ... 5.3 lb.in

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

1

Description

2
1

3

4

5

6

7

8

2
3
4

5
9

6
7
8
9

10 mm
0.394 in
9 mm
0.354 inEnd sections
1
0.039
Jumper bars
10 poles
Lateral jumper bars 2 poles
50 (IEC)
10 poles50 (IEC)
4/6 poles
50 (IEC)
4/8 poles
50 (IEC)
2/3 poles
50 (IEC)
4/7 poles
50 (IEC)
4/6 poles
50 (IEC)
4/8 poles
50 (IEC)
4/10 poles 50 (IEC)
3/4 poles
50 (IEC)
Test plugs
DIA 4 mm 0.157 in
DIA 4 mm 0.157 in IP20
Protecting cover kits
Protecting covers 1 m 39.4 in length
Short circuit bridges 2 poles
Terminal block
Blank card
markers

Color

End stops

Type

Grey
Grey
Black

White
Red
Dark grey
Transparent
Yellow
White

BAM4
BAZ1
EP8-STJB-ST-10P
PC8-2
PC8-10PC8-R7PC8-R8PC8-R6
PC8-R5
PC8-R1
PC8-R2
PC8-R3
PC8-R4
FC4
FC4-1
KCO
CO
SCB-ST-2P
RC810TT
RC810

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900102R0000
1SNL908310R0000
1SNA116538R1700
1SNA163313R2400
1SNA400849R0000
1SNA400850R0000
1SNA400843R0000
1SNA400842R0000
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA167860R0100
1SNA167927R1000
1SNK900624R0000
1SNK900604R0000
1SNL900602R0000
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
10
10
10
10
10
10
10
10
10
10
10
10
10
10
1
1
25
22
10

12,00
4.70
3.35
4.03
3.00
14.00
6.60
7.80
6.60
6.60
6.60
7.80
9.00
4.50
10.00
11.00
47.80
300.00
2.71
12
8.20

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 50

1SNC161190S0201 - Rev. A

Accessories

M6/8.ST1 screw clamp terminal blocks

Test disconnect with a screwdriver sliding link - 8 mm 0.315 in spacing

Description

6 mm²–– Secure your disconnect operations with the disconnect sliding link operated with a screwdriver,–– Ease your test operations with the 2 independent built-in test sockets compatible with DIA 4 mm 0.157 in test
plugs.

8 AWG

Ordering details
1SNC161213F0014

Description

Color

Type

Disconnect

With 2 test sockets
DIA 4 mm 0.157 in

M6/8.ST1Grey

1SNA115237R1000

Main technical data

1 conductor
per clamp

56 2.21"53.5 2.11"

48.5 1.91"

25

Weight(1 pce) g
30.00

Mounting instructions

Rigid: Solid/Stranded
0.5-10 mm²
Flexible without ferrule
0.5-6 mm²
Flexible with insulated ferrule
Gauge
A5

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

18 - 8 AWG

18-8 AWG

Wire stripping
length13 mm
0.51 inScrew clamp
Tool

Flat screwdriverØ 5 mmØ 0.197 in
0.8 - 1 N.m
7.1 - 8.9 lb.in
Flat screwdriverØ 3.5 mm
Ø 0.138 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

77 3.03"36 1.42"

Pkg
pce

IEC
M6/8.ST

Part Number

TorqueRated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

40 A / 6 mm²

30 A / 8 AWG

30 A / 8 AWG

720 A
630 V

150 V

150 V

NEMA

Disconnect device
Tool
Torque

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

41 1.61"CE

8 mm 0.315 in spacing

RoHS

USR

CSA

Gost R

Accessories
Description
1

2

3

4

5

6

Color

Type

Part Number

Pkg
pce

1
2
3

10 mm
9 mm
End sections
1 mm
Lateral jumper bars 50 A

45

Circuit separators 3 mm
0.118 in
Test plugs
DIA 4 mm 0.157 in IP20

End stops

0.394 in
0.354 in
0.039 in

Dark grey
Grey
Black

Grey
Red
Yellow
Black
Green

7

Grey
Blue
Red
White
PurpleBrown

6
7

Short circuit plugs DIA 4 mm 0.157 in
Terminal block
Blank card
markers
2 poles
3 poles
4 polesWhite
Yellow

BAM4
BAZ1
FEMT2
PC8-10PC8-R1
PC8-R2
PC8-R3
PC8-R4
SCFT2
FC4-1
AJS9
AJS9-BK
AJS9-GN
AJS9-GRAJS9-BLAJS9-RDAJS9-WH
AJS9-PR
AJS9-BR
BP8.A4
RC810TT
RC810
SC-JB8-2
SC-JB8-3
SC-JB8-4

1SNK900001R0000
1SNK900002R0000
1SNA113629R2700
1SNA163313R2400
1SNA400711R0600
1SNA400712R0700
1SNA400713R0000
1SNA400724R0300
1SNA114522R0500
1SNA167927R1000
1SNA179726R0200
1SNA206680R1500
1SNA206681R0200
1SNA206682R0300
1SNA206683R0400
1SNA206720R1400
1SNA206765R0000
1SNA206772R0000
1SNA206782R0000
1SNA173888R2000
1SNA234600R1000
1SNA234000R0200
1SNK900652R0000
1SNK900653R0000
1SNK900654R0000

50
50
10
10
10
10
10
10
20
10
25
25
25
25
25
25
25
25
25
10
22
1
25
25
25

Weight(1 pce) g
14.00
4.70
2.00
14.00
6.60
7.84
9.00
4.50
11.00
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
3.60
12
8.20
2.00
3.4
4.7

Feed-through screw clamp terminal blocks
Description

Color

Type

Part Number

Pkg
pce

Feed-throughProfile aligned with M6/8.ST...

Grey

M6/8.ST7

1SNA115243R2600

25

Weight(1 pce) g
20.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 51

1SNC161109S0201 - Rev. A

Complete list of accessories is indicated in the terminal block datasheet.
Same accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

SNACompact Terminal blocks
Fuse terminal blocks

OPTIMIZE THE PROTECTION AND
DISTRIBUTION OF YOUR CONTROL CIRCUIT
Our fuse terminal block complies with the latest evolution of the international standards
IEC 60947-7-3 ("Ancillary equipment safety requirements for fuse terminal block") which fixes
precise temperature constraint for short-circuit and overload protection.
The fuse holder accepts standard 5 x 20 mm fuses in a compact rotative holder.

FULLY ALIGNEDPERFORMANT BLOWN FUSE INDICATORSThe fuse terminal block well aligned with our standard
feed-through, disconnect and ground terminal block.

Low leakage current (< 0.5 mA) allows the protection of low
current circuits such as PLC's inputs without any risk ofcircuit disturbances.
Two voltages available (24 V and 250 V).

• Ease your installation when wiring and marking• Ease the potential distribution• Ease identification with marker on fuse holder
and disconnect lever• Ease your service maintenance with greater
accessibility and visibility.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

1SNC160230S0201 - Rev. A

FULLY ALIGNED TO EASE
POTENTIAL DISTRIBUTION

PAGE 52

C4/6.SF screw clamp terminal blocks
Fuse - 6 mm 0.24 in spacing

COMPACT

Description

4 mm²–– Protect your circuits with 5x20 fuse terminal block compliant with IEC 60947-7-3 (fuse not supplied with theterminal blocks),–– Same profile as C2.5/5 or C4/6 feed through terminal block for aligned marking and wiring

10 AWG

Ordering details
Description

1SNC161334V0014

Fuse

Color

Profile aligned with C2.5/5 and C4/6 feedthrough and groundType

Grey, black

C4/6.SF

Main technical data
UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section

0.2 ... 6 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²A4
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

500 V
6000 VIP20

78 3.07"85.5 3.37"

64.7 2.55"

Separatearrangement

24 ... 10 AWG
24 … 12 AWG
24 ... 14 AWG

Tool

24 ... 16 AWG
16 A / 10 AWG

Weight(1 pce) g

50

11.8

TH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 inTorque0.65 N.m ± 0.15
5.75 lb.in ± 1.35

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

300 V
NEMA 1

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Pkg
qty

Mounting instructions
IEC

Rated voltage
Impulse withstand voltage
Protection

72.2 2.84"

1SNL606410R0000

Connecting capacity

C4/6.SF

43.6 1.72"

Part Numbers

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

17.5 0.69"

6 mm 0.24 in spacing

1

Description

2
1

3

4

2
3

4

10 mm
9 mm
End sections
1
Lateral jumper bars 2 poles
3 poles
4 poles
10 poles25 poles
50 polesTerminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.039
35 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
24 (IEC)
24 (IEC)

Grey
Grey
Grey

Black
White

Type
BAM4
BAZ1
EP5-6
PC6-2
PC6-3
PC6-4
PC6-10LJB6-25E
LJB6-50
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNL906751R0000
1SNL906750R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
22
10

12,00
4.70
1.6
2.00
2.00
3.00
8.00
17.5
25.5
12
7.50

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 53

1SNC161186S0201 - Rev. A

Accessories

C4/6.SFD screw clamp terminal blocks
Fuse - 6 mm 0.24 in spacing

COMPACT

Description

4 mm²–– Protect your circuits with 5x20 fuse terminal block compliant with IEC 60947-7-3 (fuse not supplied with theterminal blocks),–– Same profile as C2.5/5 or C4/6 feed through terminal block for aligned marking and wiring,–– Quickly identify the defective circuit thanks to the blown fuse indicator (with leackage current <0.5mA).

10 AWG

Ordering details
Description

1SNC161335V0014

Fuse

C4/6.SFD

Colorwith blown fuse indicator 24 V AC / DCwith blown fuse indicator 250 V AC / DC

78 3.07"85.5 3.37"

64.7 2.55"

C4/6.SFD24
C4/6.SFD250

Part Numbers
1SNL606411R0000
1SNL606412R0000

IEC

UL - CSA

Rail

Rigid - Solid / Stranded
Flexiblewith non insulated ferrulewith insulated ferruleGauge
2 conductors Rigid - Solid / Stranded
Flexible
per clampwith twin ferrule
Rated current / Rated cross section

0.2 ... 6 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²
0.2 ... 4 mm²A4
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
0.2 ... 2.5 mm²
6.3 A / 4 mm²

24 ... 10 AWG

Wire stripping
length1 conductor
per clamp

500 V
6000 V
IP20

24 ... 10 AWG
24 … 12 AWG
24 ... 14 AWG

Tool

24 ... 16 AWG
16 A / 10 AWG

Weightqty(1 pce) g

50
50

12.3
12.3

TH 35-7.5,
TH 35-15
10 mm
0.39 inFlat screwdriverØ 4 mmØ 0.16 inTorque0.65 N.m ± 0.15
5.75 lb.in ± 1.35

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

Overload and short-circuit
protection

2.5 W

Exclusive short-circuit protection

4W

300 V
NEMA 1

Assembly composed of 1 fuse terminal block in
between non fuse terminal blocks

Compoundarrangement

Pkg

Mounting instructions

Connecting capacity

Separatearrangement

72.2 2.84"

Grey, black

Main technical data

Rated voltage
Impulse withstand voltage
Protection

43.6 1.72"

Type

Assembly composed of 5 fuse terminal blocks

The connecting capacity data for one Rigid - Solid / Stranded - Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

EAC

17.5 0.69"

6 mm 0.24 in spacing

1

Description

2
1

3

4

2
3

4

10 mm
9 mm
End sections
1
Lateral jumper bars 2 poles
3 poles
4 poles
10 poles25 poles
50 polesTerminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in
0.039
35 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)
24 (IEC)
24 (IEC)

Grey
Grey
Grey

Black
White

Type
BAM4
BAZ1
EP5-6
PC6-2
PC6-3
PC6-4
PC6-10LJB6-25E
LJB6-50
RC610TT
RC610

Part Numbers
1SNK900001R0000
1SNK900002R0000
1SNL900100R0000
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600
1SNL906751R0000
1SNL906750R0000
1SNA233600R1700
1SNA233000R0100

Pkg

Weightqty(1 pce) g

50
50
20
10
10
10
10
10
10
22
10

12,00
4.70
1.6
2.00
2.00
3.00
8.00
17.5
25.5
12
7.50

Complete list of accessories is indicated in the terminal block datasheet including end stops.
Some accessories such as jumper bars may modify the terminal block's ratings: Complete information available in the accessories section of the catalog.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 54

1SNC161187S0201 - Rev. A

Accessories

C4/8.SF screw clamp terminal blocks

For 5 x 20 and 5 x 25 fuses - 8 mm 0.315 in spacing

Description

4 mm²
12 AWG

Protect your circuits with 5x20 and 5x25 fuse terminal blocks (fuse not supplied with terminal blocks).

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161193F0014

Fuse

C4/8.SF

56.5 2.22"

C4/8.SF

1SNL608410R0000

Main technical data
1 conductor
per clamp

50

Mounting instructions

Connecting capacity

IEC

Rigid: Solid/Stranded
0.5-6 mm²
Flexible without ferrule
0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

180°

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

22-12 AWG

24-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

6.3 A / 4 mm²

15 A / 12 AWG 10 A / 12 AWG

630 V
8000 V
IP20

600 V

250 V

NEMA 153.5 2.10"
56
2.20"

98.5 3.89"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

CSA

Gost R

48.5
1.90"

91 3.58"

96 3.78"

Grey

Weight(1 pce) g
14.00

26 1.03"31 1.22"8 mm 0.315 in spacing

Accessories
Description
2

3

4

5

6

1
2
3
4
5

6

7

9

8

7
8
9

10 mm
9 mm
End sections
1.5 mmJumper bars
1 poles
Lateral jumper bars 10 poles
Fuses
0.5 A
3.15 A
1A
2A
5A
Assembly rods
2 poles
3 poles
4 poles
Neutral cartridges
Spring retaining rings
Terminal block
Blank card
markers
End stops

Color
0.394 in
0.354 in0.059 in
24 A
35 A

Grey
Grey
Grey

Type
BAM4
BAZ1
FEM8S
AD2.5
PC81-10
FU520

TGA8

White

CN5
ANT
RC810TT
RC810

Part Number
1SNK900001R0000
1SNK900002R0000
1SNA116951R1500
1SNA114205R2000
1SNA173523R1100
1SNA008288R1500
1SNA008289R1600
1SNA008290R1300
1SNA008291R0000
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA179371R1600
1SNA168675R1400
1SNA234600R1000
1SNA234000R0200

Pkg

Weightqty(1 pce) g

50
50
20
50
10
10
10
10
10
10
10
10
10
10
10
22
10

12.00
4.70
2.60
1.60
5.00

1.00
3.90
12
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Feed-through screw clamp terminal blocks
Description

Color

Feed-through

Type
Grey

M4/8

Part Number
1SNA115523R0700

Pkg

Weightqty(1 pce) g

50

11.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 55

1SNC161053S0201 - Rev. C1

M4/8.SFD3 screw clamp terminal blocks

For 5x20 and 5x25 fuses - With blown fuse indicator - 8 mm 0.315 in spacing

Description

4 mm²–– Protect your circuits with 5x20 and 5x25 fuse terminal blocks (fuse not supplied with terminal blocks),–– Quickly identify the defective circuit thanks to the blown fuse indicator.

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161161F0014

Fuse

53.5 2.10"
56
2.20"

98.5 3.89"

50

UL

CSA

Rigid: Solid/Stranded
0.5-6 mm²
Flexible without ferrule
0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rail

G32, TH 35-7.5,
TH 35-15

Wire stripping
length

9.5 mm
0.374 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

6.3 A / 4 mm²
400 V
4000 V
IP20

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

48.5
1.90"

96 3.78"

91 3.58"

IEC

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

180°

1SNA115935R0400

Mounting instructions

Connecting capacity

M4/8.SF

56.5 2.22"

M4/8.SFD3

Grey

Main technical data
1 conductor
per clamp

26 1.03"

With blown fuse indicatorby LED 24-60 V DC/
110 V AC

Weight(1 pce) g
14.00

CE

RoHS

Gost R

Notes

31 1.22"

Blocks with LED indicator are labeled "+" on the outside of the lever. The indicator can be reversed in the field if
required.
Leakage current: 24 V: < 0.5 mA / 110 V: < 2.2 mA

8 mm 0.315 in spacing

Accessories
2

3

4

5

6

8

Type

Part Number

Pkg
qty

1
2
3
4
5

6
7

Color

7
8

10 mm
9 mm
End sections
1.5 mmJumper bars
1 poles
Lateral jumper bars 10 poles
Fuses
0.5 A
3.15 A
1A
2A
5A
Assembly rods
2 poles
3 poles
4 poles
Spring retaining rings
Terminal block
Blank card
markers
End stops

0.394 in
0.354 in0.059 in
24 A
35 A

Grey
Grey
Grey

BAM4
BAZ1
FEM8S
AD2.5
PC81-10
FU520

TGA8

White

ANT
RC810TT
RC810

1SNK900001R0000
1SNK900002R0000
1SNA116951R1500
1SNA114205R2000
1SNA173523R1100
1SNA008288R1500
1SNA008289R1600
1SNA008290R1300
1SNA008291R0000
1SNA008292R0100
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA168675R1400
1SNA234600R1000
1SNA234000R0200

50
50
20
50
10
10
10
10
10
10
10
10
10
10
22
1

Weight(1 pce) g
12.00
4.70
2.60
1.60
5.00

1.00

12
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 56

1SNC161075S0201 - Rev. C

Description1

M4/8.SF screw clamp terminal blocks

For 5x20 and 5x25 fuses - With blown fuse indicator - 8 mm 0.315 in spacing

4 mm²

With blown fuse indicator

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

Grey

M4/8.SFL

1SNA115661R2100

50

Weight(1 pce) g
14.00

Grey

M4/8.SFD

1SNA115663R2300

50

14.00

qty

Fuse

With blown fuse indicatorby neon 110-230 V AC
With blown fuse indicator by LED 24 V AC/DC

Main technical data
Rated voltage
Impulse withstand voltage
Protection

IEC
400 V
4000 V
IP20
C

CE

USR

RoHS

UL
600 V

CSA
250 V

NEMA 1

Leakage current:
24 V : < 4.5 mA
110 V : < 0.5 mA
230 V : < 0.7 mA

US

cCSAusGost R

8 mm 0.315 in spacing

4 mm²

With blown fuse indicator and 2 test socket DIA 2 mm 0.079 in

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg

Grey

M4/8.SFDT1SNA115665R2500

50

Weight(1 pce) g
14.00

Grey

M4/8.SFLT

1SNA115667R2700

50

14.00

qty

Fuse

With blown fuse indicator by
LED 24 V AC/DC and 2 test
socket DIA 2 mm 0.079 inWith blown fuse indicator byneon 110-230 V AC and 2 test
socket DIA 2 mm 0.079 in

Main technical data
Rated voltage
Impulse withstand voltage
Protection
8 mm 0.315 in spacing

CE

RoHS

IEC
400 V
4000 V
IP20
USR

CSA

UL
600 V

CSA
250 V

NEMA 1

Leakage current:
24 V : < 4.5 mA
110 V : < 0.5 mA
230 V : < 0.7 mA

Gost R

Accessories
Description

Color

Type

Part Number

Pkg
qty

1

Test plugs

DIA 2 mm 0.079 in

Black

FC2

1SNA007865R2600

Weight(1 pce) g

100

1SNC161105S0201 - Rev. B

1

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 57

M4/8.D2.SF screw clamp terminal blocks

For 5 x 20 and 5 x 25 fuses - 8 mm 0.315 in spacing

Description

4 mm²–– Protect your circuits with 5x20 and 5x25 fuse terminal blocks (fuse not supplied with terminal blocks),–– Save space with double deck terminal blocks: 2 independent circuits 1 fuse on upper deck + 1 feed-through.

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

1SNC161082F0014

Fuse

71.5 2.81"
74
2.91"

116.5 4.59"

IEC

Rigid: Solid/Stranded
0.5-6 mm²
Flexible without ferrule
0.5-4 mm²
Flexible with insulated ferrule
Gauge
A4

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

24-12 AWG

24-12 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 N.m
4.4 - 7.1 lb.in

6.3 A / 4 mm²

20 A / 12 AWG 10 A / 12 AWG

630 V
8000 V
IP20

300 V

250 V

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com

66.5
2.62"

114 4.49"

50

Mounting instructions

Connecting capacity

M4/8.D2.SF

109 4.29"

1SNA115604R2100

Main technical data
1 conductor
per clamp

85.7 3.37"

M4/8.D2.SF

Grey

Weight(1 pce) g
26.00

CE

RoHS

USR CNR

CSA

Gost R

42 1.65"
47 1.85"

8 mm 0.315 in spacing

Accessories
2

3

4

5

6

7

8

9

11

10

Color

Type

Part Number

Pkg
qty

1
2
3

12 mm
0.472 in
1.5 mm
0.059 in
2 poles
41 A
3 poles
4 poles
10 poles
4 Lateral jumper bars 10 poles
35 A
5 Cross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 in
6 Test sockets
DIA 2 mm 0.079 in
DIA 3 mm 0.120 in
DIA 4 mm 0.157 in
7 Fuses
0.5 A
1A
2A
8 Assembly rods
2 poles
3 poles
4 poles
9 Neutral cartridges
10 Spring retaining rings
11 Terminal block
Blank card
markers
End stops
End sections
Jumper bars

Grey
Grey

BAZH1
FEM8D2S
BJMI8-2
BJMI8-3
BJMI8-4
BJMI8-10
PC81-10EL6
AL2
AL3
AL4-M3
FU520
TGA8

White

CN5
ANT
RC810TT
RC810

1SNK900102R0000
1SNA116913R0700
1SNA176669R1600
1SNA176670R1300
1SNA176671R0000
1SNA176673R0200
1SNA173523R1100
1SNA173627R2100
1SNA163043R2100
1SNA163261R0000
1SNA206721R0100
1SNA008288R1500
1SNA008290R1300
1SNA008291R0000
1SNA168672R1100
1SNA168673R1200
1SNA168674R1300
1SNA179371R1600
1SNA168675R1400
1SNA234600R1000
1SNA234000R0200

50
20
10
10
10
10
10
10
50
50
50
10
10
10
10
10
10
10
10
22
1

Weight(1 pce) g
24.00
10.00
4.50
6.00
10.00
20.00
5.00
0.10
0.90
1.20
1.10

1.00
3.90
12
8.20

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 58

1SNC161112S0201 - Rev. C

Description1

M4/8.D2.SF screw clamp terminal blocks

For 5 x 20 and 5 x 25 fuses - with blown fuse indicator - 8 mm 0.315 in spacing

4 mm²

With blown fuse indicator by LED
Ordering details
Description

Color

Type

Part Number

Pkg
qty

Fuse

With blown fuse indicatorby LED 24-60 V DC /110 V AC

Main technical data
Rated voltage
Impulse withstand voltage
Protection
CE

8 mm 0.315 in spacing

Grey

IEC
500 V
6000 V
IP20

RoHS

M4/8.D2.SFD3UL

1SNA115936R0500

CSA

NEMA 1

50

Leakage current:
24 V : < 0.5 mA
110 V : < 2.2 mA

Gost R

4 mm²

With blown fuse indicator by neon

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

Fuse

With blown fuse indicatorby neon 110-230 V AC

Main technical data
Rated voltage
Impulse withstand voltage
Protection
CE

RoHS

Weight(1 pce) g
30.00

Grey

IEC
500 V
6000 VIP20
USR CNR

CSA

M4/8.D2.SFL
UL
300 V

1SNA115646R2200
CSA
250 V

NEMA 150

Weight(1 pce) g
30.00

Leakage current:
110 V : < 0.5 mA
230 V : < 0.7 mA

Gost R

8 mm 0.315 in spacing

4 mm²

With blown fuse indicator

12 AWG

Ordering details
Description

Color

Type

Part Number

Pkg
qty

With blown fuse indicatorby LED 24 V AC/DC

Main technical data
Rated voltage
Impulse withstand voltage
Protection
CE

RoHS

Grey

IEC
500 V
6000 V
IP20
CSA

M4/8.D2.SFD
UL

1SNA115647R2300
CSA
250 V

50

Leakage current:
24 V : < 4.5 mA

1SNC161106S0201 - Rev. B

Fuse

Weight(1 pce) g
30.00

NEMA 1Gost R

8 mm 0.315 in spacing
Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 59

MTC6 thermocouple terminal blocks
Screw clamp - 6 mm 0.236 in spacing

Description–– Block adapted to many type of thermocouples,–– Allow thermocouple wire extention with no loss of signal integrity,–– Compatible with solid type thermocouple wires,–– Reduced inventory: only one part number needed for all configurations.

Ordering details
1SNC161032F0014

Description

Color

Feed-through

TypePart Number

MTC6
MTC6.ExGrey

1SNA115206R2200
1SNA146227R2500

Main technical data

Pkg
pce

Weight(1 pce) g

50
50

20
20

Mounting instructions
NFC

Rail

DIN

2 rigid thermocouple conductors
0.9 to 1.5
500 V
550 V IEC/EN 60079-7 - IM2/M1 II 2 GD/1 GD Ex e I/II

Wire size
MTC6

Rated voltage
Rated voltage Ex e (MTC6.Ex)

Wire stripping
lengthTorqueG32, TH 35-7.5,
TH 35-15
31 mm
1.22 in
0.4 - 0.6 N.m
3.5 - 5.3 lb.in

44.5 1.75"

48
1.88"

53 2.08"
55.5
2.18"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
RoHS

Gost R

Notes
Universal terminal block

Length stripped

Other thermocouple terminal blocks are available with hardware(screws, clamps and connecting bar) which match the thermocouple material being used. This requires inventory of manydifferent terminal block types.

31 1.22"

18 0.71"

Wire
insulating

23 0.91"

Iron

Iron

6 mm 0.236 in spacing
MTC 6
Terminal block 1

To temperaturesensing
instrument

Thermocouple

Constantan

Constantan

MTC 6
Terminal block 2

Figure 1: MTC6 with shield connector

1.6 0.06"

lengthstripped

3.3 0.13"

31 1.22"90°

Screw clamp

Principle ofconnection

MTC6 terminal block adapts to all thermocouple material.
This "neutral" method of connection limits the introduction offoreign materials to an insignificant level. The thermocouple wire
insulation is stripped (31 mm maximum) and the bar wires aresuperimposed on each other. The thermocouple wires are incontact over their complete 31 mm length and tightened at two
points by round tip screws (see figure 1). The screws, made ofplated brass, have only a mechanical function, that of holding thewires together with a point contact. Thus, the pressure points
are not relevant in the connection environment. One thermocouple lead connects through one terminal block (see figure 1). The
MTC6 requires only 6 mm of space, allowing 50 terminals perfoot of rail.
Thermocouple shield wire connector bar
The MTC6 can be field or factory equipped with a shield connector bar (see figure 2). This bar, made of treated brass, fits in thelower part of the terminal block. It provides for the continuity ofthe thermocouple wire shield through the terminal block or to theground with no additional spacing.

Figure 2

Description
1

2

Color

Type

Part Number

Pkg
pce

1
2
3

End sections
2.8 mm0.110 inShield connectors
Terminal block
Blank card
markers

Grey
White

FEM6
CBM5
RC610TT
RC610

1SNA118368R1600
1SNA178745R1400
1SNA233600R1700
1SNA233000R0100

20
50
22
10

Weight(1 pce) g
2.40
12
7.50

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 60

1SNC161121S0201- Rev. C

Accessories

D2.5/6.D screw clamp terminal blocks
Sensors / Actuators - 6 mm 0.236 in spacing

2.5 mm²
12 AWG

Description
Save space with triple deck terminal blocks: adapted for 3 wires sensor/actuator in just 6 mm 0.236 in spacing.

Ordering details
Description

1SNC161093F0014

Sensor51 2.01"

58.5 2.30"

81 3.19"

For 3 wire sensor witha jumper channel oneach deck

Type
Grey

Part Number

D2.5/6.D

1SNA115542R1200

Main technical data

Pkg

Weightpce(1 pce) g

25

10.00

Mounting instructions
IEC

1 conductor
per clamp

D2.5/6.D

Color

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

36.5 1.44"

RoHS

USR

CSA

Gost R

6 mm 0.236 in spacing

Accessories
Description
1

3

5

2

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block
Blank card
markers
End stops
End sections
Jumper bars

Color

Type

Grey

BAZH1
FED3E
BJD6

White

EL61
CPMF05105
RC65

Dark grey

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA235618R0000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
5
10
22
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
1.91
3.60

1SNC161148S0201 - Rev. B

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 61

D2.5/6.DL screw clamp terminal blocks
Sensors / Actuators - 6 mm 0.236 in spacing

2.5 mm²
12 AWG

Description–– Save space with triple deck terminal blocks: adapted for 3 wires sensor/actuator in just 6 mm 0.236 in
spacing,–– Quickly identify the signal circuit status thanks to the indicator.

Ordering details
1SNC161225F0014

Description
SensorColor
For 3 wire sensor
PNP with red 24 V DC
LED and a jumper bar
channel on middle andlower deck

Type
Grey

Part Number

D2.5/6.DL

1SNA115537R0500

Main technical data

58.5 2.30"
51 2.01"(1 pce) g

25

10.00

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-2.5 mm²
Flexible with insulated ferrule
Gauge
A2

UL

CSA

Rail

G32, TH 35-7.5,
TH 35-15

20-12 AWG

22-14 AWG

Wire stripping
length6 mm
0.24 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

81 3.19"36.5 1.44"

Weightpce

Mounting instructions
IEC

D2.5/6.D

1 conductor
per clamp

Pkg

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

22 A / 2.5 mm² 26 A / 12 AWG 20 A / 14 AWG
300 A
Torque
380 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 1

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

6 mm 0.236 in spacing

RoHS

USR

CSA

Gost R

Accessories
Description

3

5

2

1
2
3

4

4
5

10 mm
0.394 in
3 mm
0.118 in
2 poles
22 A
3 poles
4 poles
5 poles
10 poles20 polesCross spacing jumpers 5 mm 0.200 in - 6 mm 0.236 in - 8 mm 0.315 inTerminal block
Blank card
markers
End stops
End sections
Jumper bars

Type

Grey

BAZH1
FED3E
BJD6

White

EL61
CPMF05105
RC65

Dark grey

Part Number
1SNK900102R0000
1SNA116771R2000
1SNA178024R2500
1SNA178025R2600
1SNA178026R2700
1SNA178027R2000
1SNA178032R2500
1SNA178033R2600
1SNA177812R1700
1SNA235618R0000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

20
20
10
10
10
10
10
5
10
22
1

24.00
3.80
1.00
2.00
2.00
3.00
6.00
12.00
0.10
1.91
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161146S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 62

SNACompact Terminal blocks
Marshalling cabinets application

A COMPACTAND ALIGNEDSOLUTION FOR
YOUR CONTROLSYSTEM
Marshalling cabinets typically require the use of a large number of digital or analog signals as well as actuator's
outputs. Indeed, marshalling cabinets provide for an important cross wiring function, since the incoming fieldsignal and the channel quantity of the I/O card of the controller (DCS, large PLC's) is always different.
They facilitate the maintenance operations and ease the system modifications.
The SNACompact terminal blocks specially designed for DCS marshalling application now include a full set ofaligned terminal blocks: fuse, disconnect, feed-through and ground terminal blocks with identical profile toprovide compact and convenient solution. With a spacing of only 6 mm they reduce the required space in yourcabinet. Dedicated lateral jumper bars help the jumpering between adjacent or alternate terminal blocks.

TYPICAL MARSHALLING CONFIGURATIONSDIGITAL SIGNALSANALOG

Signal protection with fuse.
Potential distribution with double
special lateral jumper.

+

-

-

5

-

+

+

5

1

3

Load

C4/6

2
Load

Load

Load

2

C4/6.SF...

4
Load

Load

3

C4/6.S

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

Load

4

C4/6.P

Load

Load

5

LJB6-xx

PAGE 63

1SNC160231S0201 - Rev. A

2

1

Ground terminal blocks allow reliable
connection of cable shields to the groundsparing the use of external shield bar.
Potential distribution for analog signal.

Fuse and disconnect function
to allow isolation of theelectrical circuit.

DR1.5/4 screw clamp terminal blocks
Miniblocks - 4 mm 0.157 in spacing

1.5 mm²

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

1SNC161141F0014

Miniblocks

DR1.5/4

Color
Feed-through

GreyPart Number

DR1.5/4

1SNA110106R2500

Main technical data
1 conductor
per clamp

Pkg

Weightpce(1 pce) g

50

3.00

Mounting instructions
IEC

UL

CSA

Rigid: Solid/Stranded
0.2-1.5 mm²
Flexible without ferrule 0.22-1.5 mm²
Flexible with insulated ferrule
Gauge
A1

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

28 1.10"Type

17.5 A / 1.5 mm²
180 A
500 V
6000 V
IP20
NEMA 1

Rail

TH 15-5.5

Wire stripping
length7 mm
0.275 inTool

Flat screwdriverØ 2.5 mm
Ø 0.98 in

Torque0.4 - 0.6 Nm
3.5 - 5.3 lb.in

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
31 1.22"CE

RoHS

Gost R

4 mm 0.157 in spacing

Accessories
Description

3

2

1
2
3

4
4
5

6.5 mm
1 mm
2 poles
3 poles
5 poles
10 polesCircuit separators 0.3 mm
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

0.256 in
0.039 in17.5 A

Grey

0.012 in

White

Grey

White

Type
BADRL
FED2-4BJM4SCDR61
CPMF05105
RC410

Part Number
1SNA199420R2100
1SNA215580R2100
1SNA205735R0600
1SNA205736R0700
1SNA205737R0000
1SNA205738R1100
1SNA173016R1000
1SNA235618R0000
1SNA229000R1500

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
25
22
1

2.00
1.40
1.00
2.00
3.00
6.00
0.40
1.91
5.16

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161125S0201 - Rev. B

1

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 64

DR1.5/5 screw clamp terminal blocks
Miniblocks - 5 mm 0.197 in spacing

1.5 mm²
12 AWG

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

1SNC161255F0014

Miniblocks

Color
Feed-through

Type
Grey

Part Number

DR1.5/5

1SNA115510R1600

Main technical data

100

5.00

Rigid: Solid/Stranded
0.2-2.5 mm²
Flexible without ferrule 0.22-1.5 mm²
Flexible with insulated ferrule
Gauge

UL

CSA

Rail

TH 15-5.5

28 - 12 AWG

28 - 14 AWG

Wire stripping
length

8.5 mm0.335 inTool

Flat screwdriverØ 3.5 mm
Ø 0.138 in

DR1.5/5

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

27.5 1.08"

Weight(1 pce) g

Mounting instructions
IEC

1 conductor
per clamp

Pkg
pce

20 A / 1.5 mm² 20 A / 12 AWG 20 A / 14 AWG
180 A
Torque
250 V
300 V
300 V
IP20

0.4 - 0.6 Nm
3.5 - 5.3 lb.in

NEMA 125 0.98"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
CE

RoHS

USR

CSA

Gost R

5 mm 0.197 in spacing

Accessories
Description
1

3

2

1
2
3

4
4
5

0.256 in
0.039 in
24 A

Type

Grey

BADRL
FEDR5
BJMI5DRWhite

PC51-10
CPMF05105
RC55

Grey

25 A

Part Number
1SNA199420R2100
1SNA117318R2300
1SNA176704R0200
1SNA176705R0300
1SNA176706R0400
1SNA176708R1600
1SNA167908R0600
1SNA235618R0000
1SNA230000R1200

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
10
22
1

2.00
0.80
2.00
3.00
4.00
12.00
5.00
1.91
2.90

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161145S0201 - Rev. B

5

6.5 mm
1 mm
2 poles
3 poles
4 poles
10 poles
Lateral jumper bars 10 poles
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 65

DR4/6 screw clamp terminal blocks
Miniblocks - 6 mm 0.236 in spacing

4 mm²
12 AWG

Description
Save space with compact over-all dimensions terminal block.

Ordering details
Description

Color

Type

Part Number

Pkg
pce

1SNC161099F0014

Miniblocks

Feed-throughDR4/6
DR4/6.N

Grey
Blue

1SNA110251R0500
1SNA120251R0700

Main technical data

Mounting instructions
IEC

1 conductor
per clamp

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

UL

CSA

Rail

TH 15-5.5

22 - 12 AWG

28-10 AWG

Wire stripping
length

9.5 mm0.37 inTool

Flat screwdriverØ 4 mmØ 0.157 in

Torque0.5 - 0.8 Nm
4.4 - 7.1 lb.in

DR4/6

Rated current / Rated cross section
Rated short-time withstand current (1s)
Rated voltage
Impulse withstand voltage
Protection

28 1.10"50
50Weight(1 pce) g
6.00
6.00

30 A / 4 mm²
480 A
500 V

20 A / 12 AWG 25 A / 10 AWG

IP20NEMA 1

250 V

600 V

31 1.22"

The connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when applicable) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
C

CE

RoHS

USR

US

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description

2
1
2
3

3

5

4

6

4
5
6

Color

6.5 mm
1 mm
2 poles
3 poles
4 poles
10 poles
Lateral jumper bars 10 poles
Circuit separators 0.3 mm
Terminal block
Blank card
markers
End stops
End sections
Jumper bars

0.256 in
0.039 in
32 A

Grey
Grey

35 A
0.012 in

White
White

Type
BADRL
FEDR61
BJM62

PC61-10SCDR61
CPMF05105
RC65

Part Number
1SNA199420R2100
1SNA117600R0300
1SNA173217R2600
1SNA173218R0700
1SNA173219R0000
1SNA173226R2700
1SNA163311R2200
1SNA173016R1000
1SNA235618R0000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
25
10
10
10
10
10
25
22
1

2.00
0.80
2.00
3.00
4.00
10.00
5.00
0.40
1.91
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

Ground screw clamp terminal blocks
Description
GroundColor
Profile aligned with DR4/6...

Green-yellow

Type
DR4/6.PPart Number
1SNA160496R2600

Pkg

Weightpce(1 pce) g

50

10.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 66

1SNC161126S0201 - Rev. B

1

DR4/6.P screw clamp terminal blocks
Miniblocks - 6 mm 0.236 in spacing

4 mm²
12 AWG

Description–– Save space with compact over-all dimensions terminal block,–– For DIN 2 rail,–– Reliable electrical and mechanical contact with the rail.

Ordering details

1SNC161130F0014

Description
GroundColor
Screwless rail
connection

TypePart Number
1SNA160496R2600

DR4/6.P

10.00

IEC

UL

CSA

Rail

TH 15-5.5

22-12 AWG

28-10 AWG

Wire stripping
length

9.5 mm0.37 inScrew clamp
Tool

Flat screwdriverØ 4 mmØ 0.157 in
0.5 - 0.8 N.m
4.4 - 7.1 lb.in

Rigid: Solid/Stranded
0.2-4 mm²
Flexible without ferrule
0.22-4 mm²
Flexible with insulated ferrule
Gauge

Torque31 1.22"50

DR4/6.P

Mounting instructions

4 mm²
480 A

Rated cross section
Rated short-time withstand current (1s)

28 1.10"Weight(1 pce) g

Green-yellow

Main technical data
1 conductor
per clamp

Pkg
pce

12 AWG

10 AWGThe connecting capacity data for one Rigid: Solid/Stranded, or one Flexible conductor (when apply) is a mandatory information required by IEC, UL and CSA standards (Copper conductors).
All other data are provided as supplementary information only. For more details, please consult our CB, UL or CSA certificates and technical datasheet available on http://www.te.com
C

CE

RoHS

USR

US

cCSAusGost R

6 mm 0.236 in spacing

Accessories
Description
1

3

2

4

1
2
3
4
5

End stops
6.5 mmEnd sections
1 mm
Lateral jumper bars 10 poles
Circuit separators 0.3 mm
Terminal block
Blank card
markersColor
0.256 in
0.039 in
35 A
0.012 in

Grey
Grey
White
White

Type
BADRL
FEDR61
PC61-10SCDR61
CPMF05105
RC65

Part Number
1SNA199420R2100
1SNA117600R0300
1SNA163311R2200
1SNA173016R1000
1SNA235618R0000
1SNA232000R0000

Pkg

Weightpce(1 pce) g

50
25
10
25
22
1

2.00
0.80
5.00
0.40
1.91
3.60

Complete list of accessories is indicated in the terminal block datasheet.
Some accessories such as jumper bars may modify the terminal block’s ratings: complete information in the accessories catalogue pages.

1SNC161050S0201 - Rev. B

5

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 67SNACompact range

Terminal blocks Screw clamp technology

Accessories Contents
PR mounting rail................................................................................. p. 69
Screw end stops................................................................................. p. 73
Label holder......................................................................................... p. 76
BJC screw Jumper bars................................................................... p. 77

Summary_2_accessoires

PC lateral jumper bars...................................................................... p. 78

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 68PR mounting rail

Common terminal block accessories

1SNK500072F0000

Description–– Pre-punched symmetrical mounting rail,–– The slotted holes ease the mounting and allow to use existing and/or numerous fixings,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

Prepunched rail

PR30

1SNA173220R0500

Weight(1 pce) g2

328.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data

PR30

Zinc plating and passivation steel
TH 35-7.5

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

Description

1SNK500073F0000–– Symmetrical mounting rail complying with IEC60715,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

PR3.Z2

1SNA174300R1700

2

Weight(1 pce) g

718.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR3.Z2

Material
Rail

Zinc plating and passivation steel
TH 35-7.5

Equivalent E-Cu cross section

IEC
16 mm²

UL - CSA

All the main technical data provided are "manufacturer" values.
RoHS–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 69

1SNK160017S0201 - Rev. A

Mounting instructions

PR mounting rail

Common terminal block accessories

Description

1SNK500073F0000–– Symmetrical mounting rail made of galvanised steel, complying with IEC60715,–– Particularly well designed for fixing onto back-plates and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg

Weightmeter

PR3.G2

1SNA164800R0300

2(1 pce) g

718.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR3.G2

Material
Rail

Galvanised steel
TH 35-7.5

Equivalent E-Cu cross section

IEC
16 mm²

UL - CSA

All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only), fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

Description

1SNK500074F0000–– Pre-punched symmetrical mounting rail,–– The slotted holes ease the mounting and allow to use existing and/or numerous fixings.

Ordering details
Description

Color

Preprunched rail

Type
PR50

Part Number
1SNA178529R0400

Pkg

Weightmeter(1 pce) g

21288.00

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
PR50

Zinc plating and passivation steel
TH 35-15

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

2000 mm 78.74 in spacing

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 70

1SNK160040S0201 - Rev. A

Mounting instructions

PR mounting rail

Common terminal block accessories

Description

1SNK500075F0000–– Symmetrical mounting rail.

Ordering details
Description

Color

Type
PR5

Part Number
1SNA168700R2200

Pkg

Weightmeter(1 pce) g

21200.00

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Zinc plating and passivation steel
TH 35-15

Material
Rail

PR5

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

2000 mm 78.74 in spacing

1SNK500076F0000

Description–– Symmetrical mounting rail complying with IEC 60715,–– The rigidity of the rail is maximised by the 2.3 mm 0.090 in thickness of the rail, and by its solid, non slotted
construction,–– PR4 TH 35-15 is the most rigid mounting rail solution.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

Recommended for SNK ground terminal blocks up to
35 mm² 2 AWG
PR4

PR4

1SNA168500R1200

2

Weight(1 pce) g

915.00Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Material
Rail

Zinc plating and passivation steel
TH 35-15

Equivalent E-Cu cross section

IEC
50 mm²

UL - CSA
2 AWG

All the main technical data provided are "manufacturer" values.
RoHS

2000 mm 78.74 in spacing–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 71

1SNK160041S0201 - Rev. A

Mounting instructions

PR mounting rail

Common terminal block accessories

Description–– Symmetrical mounting rail.
–– Particularly well designed for fixing miniblocks and for terminal assemblies of small dimensions.

Ordering details
1SNC230057F0000

Description

Color

Type

Part Number

Pkg
meter

PR2P

1SNA206596R2500

Weight(1 pce) g

2

330

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Zinc plating and passivation steel
TH15-5.5

Material
Rail

PR2P

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.
RoHS

Mounting instructions–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing (1 mm 0.039 in rail thickness only),fixing is recommended every 250 mm 9.84 in;–– To prevent any issues during mounting, screw heads used for rail fixing should not protrude from the rail (7,5 mm 0.295 in railheight only).

2000 mm 78.74 in spacing

1SNC230058F0000

Description–– Symmetrical prepunched compact mounting rail made of passivated,–– Particularly well designed for fixing miniblocks and for terminal assemblies of small dimensions.

Ordering details
Description

Color

Type

Part Number

Pkg
meter

PR2

Recommended for SNK ground terminal blocks up to
35 mm² 2 AWG

PR2

1SNA164600R1200

2

Weight(1 pce) g

280

Please note that for all rails: 1 part number equal 1 meter (39 in). Packing of 2 meters (78 in) minimum.
Check that your order quantity is a multiple of 2.

Main technical data
Zinc plating and passivation steel
TH15-5.5

Material
Rail

IEC

UL - CSA

Equivalent E-Cu cross section
All the main technical data provided are "manufacturer" values.

2000 mm 78.74 in spacing

RoHS–– In order to guarantee the performances and security of your installation, please ensure the rail and its fixings can withstand thestatic and dynamic loads of the components mounted on it;–– To prevent the rail from flexing, fixing is recommended every 700 mm 27.6 in;–– In order to increase the accessibility of your terminal assembly, we recommend the use of our rail offset brackets EM45 (order code
1SNA008521R2600) for a 45° orientation of the rail.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 72

1SNK160103S0201

Mounting instructions

Screw end stops

Common terminal block accessories

1SNK160333V0014

BAM4 screw end stops
Description–– Give efficient support to the SNK terminal blocks assemblies thanks to the BAM4 double gripping rail contact,–– Ease the assemblies identification with the BAM4 marking location compatible with all SNK markers and labels.

Ordering details
Description

BAM4

Color

10 mm 0.394 in spacing

53.6 2.11"

Type

Dark grey

BAM4

36.2 1.42"

43.7 1.72"

Main technical data
Material specifications
Ambient temperature
min/max
26.8 1.06"

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900001R0000

Pkg

Weightqty(1 pce) g

50

14.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool
TorqueTH 35-7.5,
TH 35-15
Flat screwdriverØ 5.5 mm
Ø 0.217 in
0.9 Nm ± 0.1
7.08 lb.in ± 0.88

10 mm 0.394 in spacing

Mounting instructions

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

Blank card

In polycarbonate
In polyamide
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

White
Dark grey
Grey

Type
MC812
MC812PA
LH
LH-R1
UMH

Part Number
1SNK160000R0000
1SNK169999R0000
1SNK900605R0000
1SNK900607R0000
1SNK900611R0000

Pkg

Weightqty(1 pce) g

22
20
50
50
10

10.00
14.00
0.60
1.10
0.20

BAZH1 screw end stops
1SNK160094F0014

Description–– Give efficient support to the SNK double deck or power terminal blocks assemblies thanks to the BAZH1
double gripping rail contact,–– Ease the assemblies identification with label holders.

Ordering details
Description
BAZH1

Color

10 mm 0.394 in spacing

74.4 2.93"

Type

Dark grey

BAZH1

73.2 2.88"

65.7 2.59"

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900102R0000

Pkg

Weightqty(1 pce) g

20

24.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

Tool

TH 35-7.5
Flat screwdriverØ 5.5 mm
Ø 0.217 in

Torque1.3 Nm ± 0.1
11.4 lb.in ± 0.88

Part Number

Pkg

Weightqty(1 pce) g

22
20
50
50
10

10.00
14.00
0.60
1.10
0.20

37.2 1.46"

10 mm 0.394 in spacing
All the main technical data provided are "manufacturer" values
RoHS

Description
Blank card

In polycarbonate
In polyamide
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

Color
White
Dark grey
Grey

Type
MC812
MC812PA
LH
LH-R1
UMH

1SNK160000R0000
1SNK169999R0000
1SNK900605R0000
1SNK900607R0000
1SNK900611R0000

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 73

1SNK160026S0201 - Rev. A

Accessories

Screwless end stops

Common terminal block accessories

BAZ1 screwless end stops
1SNK160247V0014

Description–– Reduce the size of your terminal block assemblies with the screwless reduced spacing BAZ1 end stop,–– Ease the assemblies identification with various markers and label holders.

Ordering details
Description

BAZ1

Color

5.2 mm 0.205 in spacing

53.5 2.11"

Type

Dark grey

BAZ1Main technical data
43.2 1.72"

35.7 1.43"

34.2 / 1.35"

Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNK900002R0000

Pkg

Weightqty(1 pce) g

50

5.30

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail

TH 35-7.5-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

24.2 0.95"

5.2 mm 0.205 in spacing

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

compatible with HTP600
compatible with AMS600
Label holder
10 mm 0.394 in width
19.5 mm 0.768 in width
Universal wire markers holder 5.2 mm 0.205 in spacing

White
Dark grey
Grey

MC512
MC512PA
LH
LH-R1
UMH

Part Number
1SNK140000R0000
1SNK149999R0000
1SNK900605R0000
1SNK900607R0000
1SNK900611R0000

Pkg

Weightqty(1 pce) g

22
20
50
50
10

9.00
10.00
0.60
1.10
0.20

1SNK160002S0201 - Rev. A

Blank card

TypeTechnical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 74

Screw end stops

Common terminal block accessories

1SNC160644V0014

BADRL screwless end stops
Description–– Reduce the size of your terminal block assemblies with the screwless reduced spacing BADRL end stop,–– Compatible with TH15-5.5 compact rail and miniblocks.

Ordering details
Description

BADRL

Color

25 .984"

6.5 mm 0.256 in spacing

5 .197"

3.8 .150"
23.8 .937"

Type
Grey

BADRL

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Part Number
1SNA199420R2100

Pkg

Weightqty(1 pce) g

50

2.00

Mounting instructions
Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C

Rail

TH15-5,5Part Number

Pkg

Weightqty(1 pce) g

22
10

12.00
7.00

-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

6.5 mm 0.256 in spacing
All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description
compatible with HTP600
compatible with AMS600

White

Type
RC610TT
RC610

1SNA233600R1700
1SNA233000R0100

1SNK160104S0201

Blank card

Color

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 75

Label holder

Common terminal block accessories

1SNK160334V0014

LH label holder
Description–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with TE SNK end stops.

Ordering details
Description
LH

Color

10 mm 0.394 in width

10 mm 0.394 in spacing

Type

Dark grey

LHPart Number
1SNK900605R0000

Pkg

Weightqty(1 pce) g

50

0.60

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Accessories
Description

Color

White
Self-adhesive precut blank label compatible with HTP600
White
Self-adhesive precut blank compatible with HTP600
label
Yellow
Pre-printed cover marker
Protection for RCPEAD markers Transparent
White
Precut blank label
compatible with MG3
Yellow
Self-adhesive precut blank compatible with MG3
label
White
Yellow
Self-adhesive precut blank label compatible with HTP600

Type
MCLH
RCPEAD-TT
RCPEAD-TT-YL
EPR2
MG-TAR 45490
MG-TAA 49448
MG-TAA 49498
MCLH-YLPart Number
1SNK900630R0000
1SNA235158R0100
1SNA235159R0200
1SNA399726R0700
1SNB045490R8530
1SNB049448R8530
1SNB049498R8530
1SNK900633R0000

Pkg

Weightqty(1 pce) g

25
25
25
10
1650
825
825
25

10.00
9.80
12.10
4.00
0.371
0.55
0.55
10.00

1SNK160335V0014

LH-R1 label holder
Description–– Easily identify your terminal blocks assembly with white or yellow labels,–– Adjustable in height for best visibility,–– Compatible with TE SNK end stops.

Ordering details
LH-R1
19.5 mm 0.768 in spacing

Mounting instructions

Description

Color

19.5 mm 0.768 in widthType

Dark grey

LH-R1

Part Number
1SNK900607R0000

Pkg

Weightqty(1 pce) g

50

1.10

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-67 ... +230 °F-67 ... +230 °F+23 ... +104 °F

All the main technical data provided are "manufacturer" values
RoHS

Description
Self-adhesive precut blank label compatible with HTP600
Precut blank label
compatible with AMS600
Protection for RCPEB markers
Self-adhesive precut blank compatible with HTP600
label
Precut blank label
compatible with MG3
Self-adhesive precut blanklabel
Self-adhesive precut blank label compatible with HTP600

Color
White
White
Transparent
White
YellowWhite
YellowWhite
YellowType
MCLH-R1
RCPEB
EPR1
PIB2-TT
PIB2-TT-YL
MG-TAR 45194
MG-TAA 49148
MG-TAA 49198
MCLH-R1-YL

Part Number
1SNK900631R0000
1SNA178430R0500
1SNA178431R2200
1SNA235155R2600
1SNA235157R2000
1SNB045194R1735
1SNB049148R1735
1SNB049198R1735
1SNK900634R0000

Pkg

Weightqty(1 pce) g

25
1
1
25
25
900
450
450
25

10.00
0.05
9.70
9.40
0.62
0.91
0.91
10.00

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 76

1SNK160023S0201 - Rev. A

Accessories

BJCI screw jumper bars

Screw clamp terminal block accessories

1SNC160599V0014

Description
Jumper bar:–– 2, 3, 4, 5 and 10 poles available–– With IP20 protection touchproof–– Composed of captive screw on a jumper bar system–– The 10 poles jumper bar can be adapted to the number of poles required by your application.

Ordering details
BJCI

Description

Color

5.2 mm 0.205 in spacing 2 poles
3 poles
4 poles
5 poles
10 poles
6.2 mm 0.236 in spacing 2 poles
3 poles
4 poles
5 poles
10 poles24 (IEC)
24 (IEC)
24 (IEC)
24 (IEC)
24 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)
32 (IEC)

Type
Grey

Grey

BJCI5-2
BJCI5-3
BJCI5-4
BJCI5-5
BJCI5-10
BJCI6-2
BJCI6-3
BJCI6-4
BJCI6-5
BJCI6-10

Part Numbers
1SNL905602R0000
1SNL905603R0000
1SNL905604R0000
1SNL905605R0000
1SNL905610R0000
1SNL906602R0000
1SNL906603R0000
1SNL906604R0000
1SNL906605R0000
1SNL906610R0000

Pkg

Weightqty(1 pce) g

10
10
10
10
10
10
10
10
10
10

3.95
5.9
7.9
9.87
19.7
3.95
5.9
7.9
9.87
19.7

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-87 ... +230 °F-87 ... +230 °F+23 ... +104 °F

RoHS

Mounting instructions
1 - Standard use

For voltage rating > 50 V and Uimp > 2.5 KV, the bellow
accessories must be installed between two consecutive
jumpers to guarantee IP20 and voltage rating.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 77

1SNC160264S0201 - Rev. A

2 - Cut extremities
Ensure a good straight cut. by positioning the cutting
tool perpendicular to the jumper bar

PC lateral jumper bars

Screw clamp terminal block accessories

1SNC160602V0014

Description

Ordering details
Description

Color

5.2 mm 0.205 in spacing

2 poles
3 poles
4 poles
10 poles35 (IEC)
35 (IEC)
35 (IEC)
35 (IEC)

Type
Grey

PC6-2
PC6-3
PC6-4
PC6-10Part Numbers
1SNA113546R1400
1SNA116536R0500
1SNA116537R0600
1SNA113548R2600

Pkg

Weightqty(1 pce) g

10
10
10
10

2.00
2.00
3.00
8.00

Main technical data
Material specifications
Ambient temperature
min/max

Insulating material
Flammability
NF F 16 101
Service IEC 60068-2-1
Storage
Installing

Polyamide
V0
I2F2-55 ... +110 °C-55 ... +110 °C-5 ... +40 °C-87 ... +230 °F-87 ... +230 °F+23 ... +104 °F

RoHS

Mounting instructions
1 - Standard use in case of ATEX application, the lateral
jumper bar shall be connected alone (without any conductor) in the clamping unit.

2 - Cut extremities
Ensure a good straight cut. by positioning the cutting
tool perpendicular to the jumper bar

For voltage rating > 50 V and Uimp > 2.5 KV, the bellow
accessories must be installed between two consecutive
jumpers to guarantee IP20 and voltage rating.

Technical data valid for copper conductors only.

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 78

1SNC160265S0201 - Rev. A

PC

IP20 Comb jumper bar:–– Direct insertion in the screw clamp before tightening the screws, above the eventual conductor (if conductorused with ferrule, we recommend the use of long ferrule for optimized mounting ergonomy with test disconnect terminal blocks),–– Multiple versions available in pre-cut poles for test disconnect terminal blocks applications.

SNACompact range

Terminal blocks Screw clamp technology

Marking system & accessories
Contents
HTP600 thermal transfer printer.................................................. p. 80
AMS plotter.......................................................................................... p. 82
Terminal block markers.................................................................... p. 83
RC..10 terminal block markers...................................................... p. 84

Summary_3_marquage

RC55, RC65, RCAL85 terminal block markers........................ p. 85

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 79

HTP600 thermal transfer printerKit and accessories

Marking system & accessories–– The All-In-1 printer to mark many labels and markers types,–– Performance,–– High volume and serial production.
Printer kit
Description

Color

Type

Part Number

Pkg Weight

HTP600 KIT

1SNA235720R0000

1

Part Number

Pkg Weightpce

Thermal transfer printer KIT

HTP600 KIT

List of items included in the KIT
1 Black ribbon cassette
1 Cleaning cassette
1 Support plate for Entrelec terminal block markers
1 Support plate for WMTT wire markers
1 Power support cable
1 USB cableg
11000.00(1 pce)RIB1-B
HTP500-CLEAN
HTP600-PL2M
HTP600-PLM

Feeder kit
Description

Color

Type

pce

Universal feeder KIT

HTP600-FEEDER KIT

HTP600-FEEDER KIT 1SNA235721R0000

List of items included in the KIT
1 Universal feeder for marker card
1 Support plate for Entrelec terminal block markers
dedicated to feeder usage
1 Support plate for WMTT wire markers dedicatedto feeder usage
1 Support table to facilitate the cards ejection forfeeder1g2560.00(1 pce)HTP600-FEED
HTP500-PL2
HTP500-PL
HTP500-BAS

Feeder and support plates
Description

Color

Type

Part Number

Pkg WeightBlack

HTP600-FEED

1SNA235722R0000

1g530.00

Black
White

HTP600-WMTT30
HTP600-PL2M

1SNA235728R0000
1SNA235726R0000

1
1

104.00200.00White

HTP600-PLM

1SNA235724R0000

1

200.00White

HTP600-PL1M

1SNA235725R0000

1

200.00White

HTP600-BA4M

1SNA235727R0000

1

200.00White

HTP500-PL2

1SNA235705R0600

1

291.00White

HTP500-PL

1SNA235704R0500

1

294.00White

HTP500-PL1

1SNA235723R0000

1

370.00White

HTP500-BA4

1SNA235712R2400

1

290.00White

HTP500-PL3

1SNA235707R0000

1

130.00pce

HTP600-FEEDHTP600-WMTT30

HTP600-P...M

HTP500-PL...

(1 pce)1SNC160270S0201

HTP500-PL3

Universal feeder for marker card included in the
HTP600-FEEDER KIT
Feeder adapter for WMTT30 Purchased separately
Support plate for Entrelec terminal block markers
included in the HTP600 KIT
Support plate for WMTT wire markers includedin the HTP600 KIT
Support plate for TDM wire markers Purchased
separately
Support plate for BA4 wire markers Purchased
separately
Support plate for Entrelec terminal block markers
dedicated to feeder usage included in
the HTP600-FEEDER KITSupport plate for WMTT wire markers dedicated tofeeder usage included in the HTP600-FEEDER KITSupport plate for TDM wire markers dedicated tofeeder usage Purchased separately
Support plate for BA4 wire markers dedicated tofeeder usage Purchased separately
Support plate for other manufactured terminal block
markers Purchased separately

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 80

HTP600 thermal transfer printerKit and accessories

Marking system & accessories

Accessories
Description
RIB1-...

HTP500-CLEAN
HTP500-ROLL

Color

Type

Part Number

Pkg Weight

RIB1-B
RIB1-BL
RIB1-GN
RIB1-RD
HTP500-CLEAN
HTP500-ROLL
HTP500-BAS

1SNA235734R0000
1SNA235732R0000
1SNA235729R0000
1SNA235735R0000
1SNA235714R2600
1SNA235715R2700
1SNA235706R0700

1
1
1
1
1
1
1

pce

Black ribbon cassetteBlack
Blue ribbon cassetteBlue
Green ribbon cassetteGreen
Red ribbon cassetteRed
Cleaning cassetteStandard cleaning roll Ø 18
Support table to facilitate the cards ejection for feeder
included in the HTP600-FEEDER KIT

g
68.00
68.00
68.00
69.00
83.00
40.00
4060.00(1 pce)1SNC160270S0201

HTP500-BAS

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 81AMS plotter

Kit and accessories

AMS 600
Description–– For basic marking applications,–– Economic,–– Full-size format,–– Print original manufacturers' markers.
AMS 600

Ordering details
Description

Color

AMS 600 Plotter KIT
List of items included in the KIT:
1 AMS 600 plotter pen printer1 Software CD
1 Power supply cable
1 USB cable
1 Support plate for RC / MC / RCTT / WMTT /BA4 / RCT
1 Support plate for MC...PA
1 Plotter pen Ø 0.25 mm .01 in
1 Plotter pen Ø 0.35 mm .014 in
5 Ink cartridges
1 Cleaner fluid
1 Cleaner kit

Type
AMS 600 KIT

Part Number
1SNA360000R2400

Pkg

Weightpce(1 pce) g

1

12600

AMS 600AMS SOFTWAREAMS POWERAMS USB
SPRC1
SPRC 30-3
AMS PEN 0.25
AMS PEN 0.35
AMS INK CARTRIDGESAMS CLEANER FLUIDAMS CLEANER KIT

AMS 300
Description–– Basic needs,–– Economic,–– Half-size format–– Compatible with most of AMS 600 accessories.
AMS 300

Ordering details
Description

Color

AMS 300 BASIC KITPart Number
1SNA360000R2500

Pkg

Weightpce(1 pce) g

1

8800

AMS 300 BASICAMS SOFTWAREAMS POWERAMS USBSPRC2DISPOSABLE AMS PEN
ED-R 0.25
DISPOSABLE AMS PEN
ED-R 0.35

1SNC160110S0201 - Rev. A

AMS 300 Plotter KIT
List of items included in the KIT:
1 AMS 300 plotter pen printer1 Software CD
1 Power supply cable
1 USB cable
1 Support plate for BA4 / MC / RC / RCAL /RCT / RCTT
1 Disposable plotter penØ 0.25 mm .01 in EDR ink
1 Disposable plotter penØ 0.35 mm .014 in EDR ink

Type

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 82

Terminal block markers

Compatible with HTP600 printer

1SNC170021V0014

Blank markers for SNA series–– Blank marker card designated for high marking quality,–– Good marking durability in the severe environments,–– Made of rigid polycarbonate.
Dimensions
mmin

Nb. ofmarkers
per card

Color

Type

Part Number

Pkg

Weightcard(1 card) g

1SNA231600R1500
1SNA231700R1100

22
22

12.00
12.00

1SNA233600R1700
1SNA233700R1300

22
22

12.00
12.00

1SNA234600R1000
1SNA234700R1400

22
22

12.00
12.00

RCGW510

1SNA235638R0000

12

11.00

Type

Part Number

Pkg

Weightcard(1 card) g

1SNA235621R0000

22

1.91

1SNA235618R0000

22

1.91

RC510TT Blank strip Markers for 5 mm 0.197 in spacing terminal blocks and BAZ1 end stop.
5 x 105 x 100.197 x 0.394
0.197 x 0.394

48
48

White
Yellow

RC510TT
RC510TT-YL

RC610TT Blank strip Markers for 6 mm 0.236 in spacing terminal blocks
6 x 106 x 100.236 x 0.394
0.236 x 0.394

39
39

White
Yellow

RC610TT
RC610TT-YL

RC810TT Blank strip Markers for 8 mm 0.315 in and larger spacing terminal blocks and end stops
8 x 108 x 100.315 x 0.394
0.315 x 0.394

30
30

White
Yellow

RC810TT
RC810TT-YL

RCGW510 Blank Individual Marker for Entrelec RGW terminal blocks
5 x 100.197 x 0.394

45

White

–– To be directly used on terminal block assembly,–– Available in precut version to fit all applications.
Dimensions
mmin

Nb. ofmarkers
per card

Color

CPMF Blank strip label for Entrelec M6/9EE terminal blocks
105 x 7.6

4.134 x 0.299

6

White

CPMF08105

CPMF Blank strip label for Entrelec series D and ADO terminal blocks
4.134 x 0.205

10

White

CPMF05105

1SNC160268S0201

105 x 5.2

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 83

RC..10 terminal block markers

Compatible with AMS600/300 plotters

1SNC700141F0000

Description

RC510–– Blank card in polyamide,–– Terminal blocks are directly independent after strip mounting,–– To be used to mark spring clamp, ADO System® and screw clamp pluggable SNA terminal blocks.

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

For 4 mm 0.157 in terminal block spacing
RC410
10 x 40.394 x 0.157 2

7

100

White

RC410

1SNA229000R1500

10

5.20

RC510
RC510-YL

1SNA231000R0700
1SNA103890R2100

10
10

5.20
5.50

RC610
RC610
RC610
RC610
RC610
RC610

1SNA233000R0100
1SNA206233R0000
1SNA206232R0700
1SNA206231R0600
1SNA206230R1100
1SNA206235R0200

10
10
10
10
10
10

6.70
6.70
6.70
6.70
6.70
6.70

RC810

1SNA234000R0200

10

8.20

RC1010

1SNA238000R1600

10

1.30

SPRC 1

1SNA360010R1500

1

1500.00

SPRC 2

1SNA360011R1500

1

600.00For 5 mm 0.197 in terminal block spacing
RC510
10 x 50.394 x 0.197 3
4

7
4

100

White
Yellow

For 6 mm 0.236 in terminal block spacing
RC610
10 x 6
0.394 x 0.236 4

4

100

White
Blue
OrangeYellow
GreenRed

For 8 mm 0.315 in terminal block spacing
RC810
10 x 80.394 x 0.315 4

4

100

White

For 10 mm 0.394 in terminal block spacing
RC101010 x 10 0.394 x 0.394 7

7

80

White

Marking system accessories
SPRC 1
Support plate for AMS600
Included in KIT MAO AMS 600
SPRC 2
Support plate for AMS250
Included in AMS 250 BASIC KIT

1SNC160113S0201 - Rev. B

Mounting instruction

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 84

RC55, RC65, RCAL85 terminal block markers
Compatible with AMS600/300 plotters

1SNC700141F0000

Description–– Blank card in polyamide,–– Terminal blocks are directly independent after strip mounting,–– To be used to mark screw clamp (1) and spring clamp (side mounting) SNA terminal blocks, andMiniblocks.

RC55

Main technical data
Material
Polyamide

Flammability
V2

Ordering details
Dimensions
mminMaximum
printed digits
Hor.
Vert.

Nb. ofColormarkers
per card

Type

Part Number

Pkg

Weightcard(1 card) g

For 5 mm 0.197 in terminal block spacing
RC55
5x5

0.197 x 0.197 3

3

100

White

RC55

1SNA230000R1200

10

2.90

RC65
RC65
RC65

1SNA232000R0000
1SNA103775R0000
1SNA103776R0100

10
10
10

3.60
3.40
3.40

RCAL85

1SNA237000R0500

10

2.90

SPRC 1

1SNA360010R1500

1

1500.00

SPRC 2

1SNA360011R1500

1

600.00For 6 mm 0.236 in terminal block spacing
RC65
5x6

0.197 x 0.236 3

3

100

White
Blue
Red

For 8 mm 0.315 in terminal block spacing (1)
RCAL855x80.197 x 0.315 5

3

100

White

Marking system accessories
SPRC 1
Support plate for AMS600
Included in KIT MAO AMS 600

SPRC 2
Support plate for AMS250
Included in AMS 250 BASIC KIT(1) RCAL85 not compatible with screw clamp terminal blocks

1SNC160114S0201 - Rev. B

Mounting instruction

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 85

SNACompact/SNA
CrossReference table

SNACompact

SNA

New PN

Description

PN

Description

1SNL505010R0000

1SNL605010R0000

C2.5/5

1SNA115486R0300

MA2.5/5

1SNL505020R0000

1SNL605020R0000

C2.5/5.N

1SNA125486R0500

MA2.5/5.N

1SNL506011R0000

1SNL606011R0000

C2.5/6

1SNA115486R0300

MA2.5/5

1SNL506021R0000

1SNL606021R0000

C2.5/6.N

1SNA125486R0500

MA2.5/5.N

1SNL506010R0000

1SNL606010R0000

C4/6

1SNA115116R0700

M4/6

1SNL506020R0000

1SNL606020R0000

C4/6.N

1SNA125116R0100

M4/6.N

1SNL508010R0000

1SNL608010R0000

C6/8

1SNA115118R1100

M6/8

1SNL508020R0000

1SNL608020R0000

C6/8.N

1SNA125118R1300

M6/8.N

1SNL510010R0000

1SNL610010R0000

C10/10

1SNA115120R1700

M10/10

1SNL510020R0000

1SNL610020R0000

C10/10.N

1SNA125120R1100

M10/10.N

1SNL512010R0000

1SNL612010R0000

C16/12

1SNA115129R1400

M16/12

1SNL512020R0000

1SNL612020R0000

C16/12.N

1SNA125129R1600

M16/12.N

1SNL505150R0000

1SNL605150R0000

C2.5/5.P

1SNA165488R2700

MA2.5/5.P

1SNL506151R0000

1SNL606151R0000

C2.5/6.P

1SNA165488R2700

MA2.5/5.P

1SNL506150R0000

1SNL606150R0000

C4/6.P

1SNA165113R1600

M4/6.P

1SNL508150R0000

1SNL608150R0000

C6/8.P

1SNA165114R1700

M6/8.P

1SNL510150R0000

1SNL610150R0000

C10/10.P

1SNA165115R1000

M10/10.P

1SNL512150R0000

1SNL612150R0000

C16/12.P

1SNA165130R2300

M16/12.P

1SNL508310R0000

1SNL608310R0000

C6/8.ST1

1SNA115237R1000

M6/8.ST1

1SNL508311R0000

1SNL608311R0000

C6/8.ST1.IP20

1SNA115971R1000

M6/8.ST1 IP20

1SNL506410R0000

1SNL606410R0000

C4/6.SF

1SNA115657R2500

M4/8.SF

1SNL506411R0000

1SNL606411R0000

C4/6.SFD24

1SNA115935R0400

M4/8.SFD3

1SNL506412R0000

1SNL606412R0000

C4/6.SFD250

1SNA115661R2100

M4/8.SFL

1SNL506310R0000

1SNL606310R0000

C4/6.S

1SNA115986R0000

M4/6.SNB

1SNA115657R2500

1SNL608410R0000

C4/8.SF

1SNA115657R2500

M4/8.SF

CrossReference_table - Rev. A

Old PN

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

PAGE 86

IndexPart Number classification
Part Number

TypePart Number

TypePart Number

Type

1SNA007865R2600

FC2

33, 35, 39, 40,
45, 46, 57

1SNA115935R0400

M4/8.SFD3

56

Page

1SNA173530R2400

CBM5D

32, 34

1SNA008288R1500

FU520

55, 56, 58

1SNA115936R0500

M4/8.D2.SFD3

59

1SNA173627R2100

EL6

FU520

55, 56M4/6.SNB

44

13, 14, 34, 36,
37, 46, 58

1SNA008289R1600

1SNA115986R0000

11, 12, 43, 53,
54, 7851

55, 56, 58

PC6-3

BP8.A4

FU520 1A

1SNA116536R0500

1SNA173888R2000

1SNA008290R1300

1SNA174300R1700

PR3.Z269

1SNA008291R0000

FU520 2A

55, 56, 58

1SNA116537R0600

PC6-4

1SNA176259R1300

ITV5

32

1SNA008292R0100

FU520 5A

55, 56

11, 12, 43, 53,
54, 78

1SNA176663R0000

BJMI6-2

13, 14

1SNA103189R2600

SCD-WH

40

1SNA176664R0100

BJMI6-3

13, 14

1SNA103775R0000

RC65 BLUE

85

1SNA176665R0200

BJMI6-4

13, 14

1SNA103776R0100

RC65 RED

85

1SNA176666R0300

BJMI6-5

13, 14

1SNA103890R2100

RC510-YL

84

1SNA176667R0400

BJMI6-10

13, 14

1SNA105044R2100

M4/6.D2

34

1SNA176669R1600

BJMI8-2

15, 38, 58

1SNA105045R2200

M4/6.D2

34

1SNA176670R1300

BJMI8-3

15, 38, 58

1SNA105046R2300

M4/6.D2

34

1SNA176671R0000

BJMI8-4

15, 38, 58

1SNA105047R2400

M4/6.D2

34

1SNA176672R0100

BJMI8-5

15, 38

1SNA105048R0500

M4/6.D2

34

1SNA176673R0200

BJMI8-10

15, 38, 58

1SNA105049R0600

M4/6.D2

34

1SNA176675R0400

BJMI10-2

16

1SNA105053R2200

M4/6.SNB

44

1SNA176676R0500

BJMI10-3

16

1SNA105055R2400

M6/8.SNB

45

1SNA176677R0600

BJMI10-4

16

1SNA105124R1600

M35/1618

1SNA176678R1700

BJMI10-5

16

1SNA110106R2500

DR1.5/4

64

1SNA176679R1000

BJMI10-10

16

1SNA110251R0500

DR4/6

66

1SNA176704R0200

BJMI5DR-2

65

1SNA113003R1000

SCM613-17, 38

1SNA176705R0300

BJMI5DR-3

65

1SNA113373R2600

FEM 8

45

1SNA176706R0400

BJMI5DR-4

65

1SNA113482R0500

SCM6D

34

1SNA176708R1600

BJMI5DR-10

65

1SNA113542R1000

PC5-2

10, 32, 42

1SNA176736R2100

BJMI5D-2

32

1SNA113544R1200

PC5-1010, 32, 42

1SNA176737R2200

BJMI5D-3

32

1SNA113546R1400

PC6-2

11-14, 43, 53,
54, 78

1SNA176738R0300

BJMI5D-4

32

1SNA176739R0400

BJMI5D-5

32

1SNA176740R1100

BJMI5D-10

32

1SNA176791R2100

CPV4-519

1SNA176816R1200

CPV1-2

18

1SNA177812R1700

EL61

61, 62

1SNA178024R2500

BJD6-261, 62

1SNA178025R2600

BJD6-361, 62

1SNA178026R2700

BJD6-461, 62

1SNA178027R2000

BJD6-561, 62

1SNA178032R2500

BJD6-1061, 62

1SNA178033R2600

BJD6-2061, 62

1SNA116538R1700

PC8-2

15, 45, 49, 50

1SNA116539R1000

PC8-3

45

1SNA116540R2500

PC8-4

45

1SNA116576R1500

FEM 3A

13, 24

1SNA116591R0500

FEMS 6D

46

1SNA116629R2200

FEM4A

14, 25

1SNA116656R2500

FEM8D138

1SNA116720R2100

SCMA5D

32

1SNA116771R2000

FED3E

61, 62

1SNA116795R1100

SCFCV1-2

18

1SNA116797R1300

SCFCV419

1SNA116913R0700

FEM8D2S

58

1SNA116951R1500

FEM 8S55, 56

1SNA117318R2300

FEDR5

65

1SNA117600R0300

FEDR6166, 67

1SNA118368R1600

FEM615-17, 26, 27,
42, 60

1SNA118495R1700

SCF6D

34

1SNA118499R2300

FEM6 D32, 34, 36, 37

1SNA118707R0300

SCF6

42

1SNA120251R0700

DR4/6.N

66

1SNA125124R0100

M35/16.N

18

1SNA125166R1300

M4/6.D1.N

35

Page

1SNA113548R2600

PC6-10

11-14, 43, 53,
54, 78

1SNA125271R2400

M4/6.D2.N

34

1SNA113550R2400

EIP

13, 14, 32

1SNA125468R2200

M4/6.3A.N

13

1SNA113629R2700

FEMT2

51

1SNA125479R2500

M4/6.4A.N

14

1SNA125490R1500

MA2.5/5.D2.N

32

1SNA146227R2500

MTC 6.Ex

60

1SNA160496R2600

DR4/6.P66, 67

1SNA163043R2100

AL2-H12-M3

13, 14, 39, 58

1SNA163070R0000

AL2-H8.5-M3

35

1SNA163261R0000

AL3-H9.5-M3

13, 14, 35,
39, 58

1SNA163311R2200

PC61-1034, 36, 37, 40,
44, 46, 66, 67

1SNA178430R0500

RCPEB

76

1SNA178431R2200

EPR1

76

1SNA114205R2000

AD 2.541, 44, 45,
55, 56

1SNA114522R0500

SCFT2

51

1SNA114825R0500

SCFM6

28, 42, 44, 45

1SNA114994R0700

FEM62

44

1SNA115124R0700

M35/1618

1SNA115166R1100

M4/6.D1

35

1SNA115168R2300

M4/6.DD

36

1SNA115184R0400

M4/6.DD1

37

1SNA115206R2200

MTC6

60

1SNA115237R1000

M6/8.ST1

51

1SNA115243R2600

M6/8.ST7

51

1SNA115271R2200

M4/6.D2

34

1SNA115468R2000

M4/6.3A

13

1SNA115479R2300

M4/6.4A

14

1SNA115490R1300

MA2.5/5.D2

32

1SNA115498R1700

M6/8.D1

39

1SNA115501R1200

M6/8.D2

38

1SNA115510R1600

DR1.5/5

65

1SNA115523R0700

M4/8

55

1SNA115530R1200

MA2.5/5.D1.1

33

1SNA115537R0500

D2.5/6.DL

62

1SNA115542R1200

D2.5/6.D

61

1SNA115561R1500

M4/6.D2.SNBT

46

1SNA115604R2100

M4/8.D2.SF

58

1SNA115646R2200

M4/8.D2.SFL

59

1SNA115647R2300

M4/8.D2.SFD

59

1SNA115661R2100

M4/8.SFL

57

1SNA115663R2300

M4/8.SFD

57

1SNA115665R2500

M4/8.SFDT

57

1SNA115667R2700

M4/8.SFLT

57

1SNA115686R1300

M 4/6.SNB

44

1SNA115688R2500

M6/8.SNB

45

1SNA115699R2000

MA2.5/5.SNB

42

1SNA163313R2400

PC8-1015, 45, 49-51

1SNA178529R0400

PR50

70

1SNA163315R2600

PC10-1016

1SNA178745R1400

CBM542, 44, 60

1SNA164600R1200

PR2

72

1SNA179371R1600

CN555, 58

1SNA164800R0300

PR3.G270

1SNA179623R0300

BJDP1

13, 14, 18

1SNA164950R0000

AL2-H9.6-M3

33

1SNA179624R0400

BJDP2

18

1SNA165111R1400

M35/16.P

18, 291SNA179625R0500

BJDP3

13, 14

1SNA165130R2300

M16/12.P

17, 28

1SNA179626R0600

BJMI12-2

17

1SNA167319R0600

AL2-H8.5-M2.6

40

1SNA179628R1000

BJMI12-3

17

1SNA167860R0100

FC4

18, 39, 49, 50

1SNA179629R1100

BJMI12-4

17

1SNA167908R0600

PC51-1065

1SNA179630R1600

BJMI12-5

17

1SNA167927R1000

FC4-1-RD

49-51

1SNA179631R0300

BJMI12-10

17

1SNA168500R1200

PR4

71

1SNA179668R2000

BJMI6D-2

34, 36, 37, 46

1SNA168672R1100

TGA8-255, 56, 58

1SNA179669R2100

BJMI6D-3

34, 36, 37, 46

1SNA168673R1200

TGA8-355, 56, 58

1SNA179670R2600

BJMI6D-4

34, 36, 37, 46

1SNA168674R1300

TGA8-455, 56, 58

1SNA179671R1300

BJMI6D-5

34, 36, 37, 46

1SNA168675R1400

ANT

55, 56, 58

1SNA179672R1400

BJMI6D-10

34, 36, 37, 46

1SNA168700R2200

PR5

71

1SNA179726R0200

AJS9

51

1SNA173016R1000

SCDR61-WH

64, 66, 67

1SNA195124R0000

M35/16.V0

18

1SNA173217R2600

BJM62-2

40, 66

1SNA195271R2300

M4/6.D2.V0

34

1SNA173218R0700

BJM62-3

40, 66

1SNA195490R1400

MA2.5/5.D2.V0

32

1SNA173219R0000

BJM62-4

40, 66

1SNA195501R1300

M6/8.D2.V0

38

1SNA173220R0500

PR30

69

1SNA195637R1200

M4/6.3A.P.V0

13, 24

1SNA173221R2200

BJM62-5

40

1SNA195638R2300

M4/6.4A.P.V0

14, 25

1SNA173226R2700

BJM62-10

40, 66

1SNA195686R1400

M4/6.SNB.V0

44

1SNA173523R1100

PC81-1055, 56, 58

1SNA199219R0300

D4/6.T1

41

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

Index-PartNumber

Page

PAGE 87

IndexPart Number classification
Part Number

TypePart Number

TypePart Number

Type

1SNA199220R0000

D4/6.P.T1

41

Page

1SNA235727R0000

HTP600-BA4M

80

Page

1SNK900634R0000

MCLH-R1-YL

76

1SNA199420R2100

BADRL

64-67, 75

1SNA235728R0000

HTP600-WMTT30 80

1SNK900652R0000

SC-JB8-2

51

1SNA205735R0600

BJM4-264

1SNA235729R0000

RIB1-GN

81

1SNK900653R0000

SC-JB8-3

51

1SNA205736R0700

BJM4-364

1SNA235732R0000

RIB1-BL81

1SNK900654R0000

SC-JB8-4

51

1SNA205737R0000

BJM4-564

1SNA235734R0000

RIB1-B81

1SNK916302R0000

JB16-218

1SNA205738R1100

BJM4-1064

1SNA235735R0000

RIB1-RD81

1SNK916303R0000

JB16-318

1SNA206230R1100

RC 610 GREEN

84

1SNA237000R0500

RCAL8585

1SNK916304R0000

JB16-418

1SNA206231R0600

RC 610 YELLOW 84

1SNA238000R1600

RC1010

1SNK916305R0000

JB16-518

1SNA206232R0700

RC 610 ORANGE 84

16-20, 27-31,
84

1SNK916310R0000

JB16-1018

1SNA206233R0000

RC 610 BLUE84

1SNK922302R0000

JB22-2

19

1SNA206235R0200

RC 610 RED

84

1SNK922303R0000

JB22-3

19

1SNA206596R2500

PR2P

72

1SNK922305R0000

JB22-519

1SNA206680R1500

AJS9-BK

51

1SNK922310R0000

JB22-1019

1SNA206681R0200

AJS9-GN

51

1SNK926302R0000

JB26-220

1SNA206682R0300

AJS9-GR

51

1SNK926303R0000

JB26-320

1SNA206683R0400

AJS9-BL

51

1SNK926305R0000

JB26-520

1SNA206720R1400

AJS9-RD

51

1SNK926310R0000

JB26-1020

1SNA206721R0100

AL4-M358

1SNL605010R0000

C2.5/5

10

1SNA206723R0300

AL4-M418

1SNL605020R0000

C2.5/5.N

10

1SNA206765R0000

AJS9-WH

51

1SNL605150R0000

C2.5/5.P

10

1SNA206772R0000

AJS9-PR51

1SNL606010R0000

C4/6

12

1SNA206782R0000

AJS9-BR51

1SNL606011R0000

C2.5/6

11

1SNA215580R2100

FED2-464

1SNL606020R0000

C4/6.N

12

1SNA229000R1500

RC 41064, 84

1SNL606021R0000

C2.5/6.N

11

1SNA230000R1200

RC55

65, 85

1SNL606150R0000

C4/6.P

12, 23

1SNA231000R0700

RC510

10, 21, 32,
42, 84

1SNL606151R0000

C2.5/6.P

22

1SNL606310R0000

C4/6.S

43

1SNL606410R0000

C4/6.SF

53

1SNL606411R0000

C4/6.SFD24

54

1SNL606412R0000

C4/6.SFD250

54

1SNL608010R0000

C6/8

15

1SNL608020R0000

C6/8.N

15

1SNL608150R0000

C6/8.P

15, 26

1SNL608310R0000

C6/8.ST149

1SNL608311R0000

C6/8.ST1.IP20

50

1SNL608410R0000

C4/8.SF

55

1SNL610010R0000

C10/1016

1SNL610020R0000

C10/10.N

16

1SNL610150R0000

C10/10.P

16, 27

1SNL612010R0000

C16/1217

1SNL612020R0000

C16/12.N

17

1SNL900100R0000

EP5-6

10-12, 21-23,
43, 53, 54

1SNL900101R0000

CS5-6 (2.5/4mm²) 10-12

1SNL900102R0000

EP8-ST49, 50

1SNL900201R0000

STI4-YL

49

1SNA299683R0100

D4/6.T3

40

1SNA299684R0200

D4/6.T3.P

40

1SNA360000R2400

AMS 600 KIT

82

1SNA360000R2500

AMS 250 BASIC
KIT

82

1SNA360010R1500

SPRC 184, 85

1SNA360011R1500

SPRC 284, 85

1SNA399726R0700

EPR2

76

1SNA400194R2100

M35/16

18

1SNA400195R2200

M35/16

18

1SNA400196R2300

M35/16

18

1SNA400305R1000

D70/22

19

1SNA400306R1100

D70/22.N

19

1SNA400370R2400

D95/2620

1SNA400371R1100

D95/26.N

20

1SNA400620R1700

D95/26.P20, 31

1SNA400711R0600

PC8-R149-51

1SNA400712R0700

PC8-R249-51

1SNA400713R0000

PC8-R349-51

PC8-R449-51

1SNA231600R1500

RC510TT10, 32, 42, 83

1SNA231700R1100

RC510TT-YL

83

1SNA400724R0300

1SNA232000R0000

RC65

40, 61, 62, 66,
67, 85

1SNA400772R1300

D70/22.P19, 30

1SNA400789R0000

D70/22.YL

19

11-14, 22-25,
34, 36, 37, 43,
44, 46, 53, 54,
60, 75, 84

1SNA400791R0000

D95/26.YL

20

1SNA400842R0000

PC8-R549, 50

1SNA400843R0000

PC8-R649, 50

11-14, 22-24,
34, 36, 37, 43,
44, 46, 53, 54,
60, 75, 83

1SNA400849R0000

PC8-R749, 50

1SNA400850R0000

PC8-R849, 50

1SNB045194R1735

MG-TAR 45194(17x35 WH)

76

1SNB045490R8530

MG-TAR 45490(8,5x30)

76

MG-TAA 49148(17x35 YE)

76

1SNA233000R0100

1SNA233600R1700

RC610

RC610TT

1SNA233700R1300

RC610TT-YL

83

1SNA234000R0200

RC810

15, 26, 28, 29,
38, 45, 49-51,
55, 56, 58, 84

1SNA234600R1000

RC810TT

1SNB049148R1735

15-20, 26-31,
38, 45, 49-51,
55, 56, 58, 83

1SNB049198R1735

MG-TAA 49198(17x35 WH)

76

1SNB049448R8530

MG-TAA 49448(8,5x30 YE)

76

1SNB049498R8530

MG-TAA 49498(8,5x30 WH)

76

Page

RC810TT-YL

83

1SNA235155R2600

PIB2-TT76

1SNA235157R2000

PIB2-TT-YL

76

1SNA235158R0100

RCPEAD-TT

76

1SNK140000R0000

MC512

74

1SNA235159R0200

RCPEAD-TT-YL

76

1SNL900602R0000

SCB-ST-2P

49, 50

1SNK149999R0000

MC512PA74

1SNA235618R0000

CPMF05105

61, 62, 64-67,
83

1SNL900902R0000

SCB-kit49

1SNK160000R0000

MC812

73

1SNL905602R0000

BJCI5-2

10, 77

1SNA235621R0000

CPMF08105

83

1SNK169999R0000

MC812PA73

1SNL905603R0000

BJCI5-3

10, 77

1SNA235638R0000

RCGW51083

1SNK900001R0000

BAM4

1SNL905604R0000

BJCI5-4

10, 77

1SNA235704R0500

HTP500-PL

80

10-18, 22-29,
42-45, 49-51,
53-56, 73

1SNL905605R0000

BJCI5-5

10, 77

1SNA235705R0600

HTP500-PL280

1SNL905610R0000

BJCI5-10

10, 77

1SNA235706R0700

HTP500-BAS

81

1SNL906602R0000

BJCI6-2

11, 12, 77

1SNA235707R0000

HTP500-PL380

1SNL906603R0000

BJCI6-3

11, 12, 77

1SNA235712R2400

HTP500-BA480

1SNL906604R0000

BJCI6-4

11, 12, 77

1SNA235714R2600

HTP500-CLEAN

81

1SNL906605R0000

BJCI6-5

11, 12, 77

1SNA235715R2700

HTP500-ROLL

81

1SNL906610R0000

BJCI6-10

11, 12, 77

1SNA235720R0000

HTP600 KIT80

1SNL906750R0000

LJB6-50

1SNA235721R0000

HTP600-FEEDER 80
KIT

11, 12, 43,
53, 54

1SNL906751R0000

LJB6-25E

1SNA235722R0000

HTP600-FEED

80

11, 12, 43,
53, 54

1SNA235723R0000

HTP500-PL1

80

1SNL908310R0000

JB-ST-10P

49, 50

1SNA235724R0000

HTP600-PLM

80

1SNA235725R0000

HTP600-PL1M

80

1SNA235726R0000

HTP600-PL2M

80

1SNK900002R0000

1SNK900102R0000

BAZ1

BAZH1

10-18, 22-29,
42-45, 49-51,
53-56, 74
19, 20, 30-32,
34, 36-38, 40,
46, 58, 61,
62, 73

1SNK900604R0000

CO49, 50

1SNK900605R0000

LH

73, 74, 76

1SNK900607R0000

LH-R1

73, 74, 76

1SNK900611R0000

UMH

73, 74

1SNK900624R0000

KCO

49, 50

1SNK900630R0000

MCLH

76

1SNK900631R0000

MCLH-R1

76

1SNK900633R0000

MCLH-YL76

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGY

Index-PartNumber

1SNA234700R1400

PAGE 88

CONNECT WITH US
We make it easy to connect with our experts and are ready to provide all the support you need.
Visit www.te.com/support to chat with a Product Information Specialist.
Asia: +86 400-820-6015 - Europe, Middle East, & Africa: +49 6251-133-0 - North America: +1-888-441-9982

te.com© 2021 TE Connectivity. All Rights Reserved.
TE Connectivity, TE connectivity (logo) and Every Connection Counts are trademarks. All other logos, products
and/or company names referred to herein might be trademarks of their respective owners.
While TE has made every reasonable effort to ensure the accuracy of the information in this brochure, TE does
not guarantee that it is error-free, nor does TE make any other representation, warranty or guarantee thatthe information is accurate, correct, reliable or current. TE reserves the right to make any adjustments to theinformation contained herein at any time without notice. TE expressly disclaims all implied warranties regarding
the information contained herein, including, but not limited to, any implied warranties of merchantability or
fitness for a particular purpose. The dimensions in this catalog are for reference purposes only and are subject tochange without notice. Specifications are subject to change without notice. Consult TE for the latest dimensions
and design specifications.
4-1773985-2

03/21

Original

INDUSTRY / SNACOMPACT TERMINAL BLOCKS – SCREW CLAMP TECHNOLOGYCATALOGTE Connectivity
3, rue Jean Perrin
69687 Chassieu cedex
FranceTel: +33 481923100
www.te.com