Mitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)2

Development of Air-to-Water Heat Pump forHome Air conditioning/Hot Water Supply Combination Systemwith Chilled/Hot Water in European Markets- Extending Use of New Heat Pump System in Cold Regions -HIROYUKI YAMADA*1NOBUYUKI TAKEUCHI*1

MINEMASA OMURA*2

HIROFUMI ISHIZUKA*1

TAKAYUKI KOBAYASHI*3 MASASHI MAENO*4

With European heat pump manufacturer NIBE Industrier, Mitsubishi Heavy Industries,
Ltd. (MHI) has jointly developed an air conditioning/hot water supply combination system withchilled/hot water suited for European domestic use. As part of the joint development, a mutual
OEM supply system was established; the outdoor unit was developed and supplied by MHI
based on conventional air conditioner technologies and the indoor unit was supplied by NIBE.
Hot water supply systems utilizing heat pump technology are products that are attracting
attention in European heating markets, because drastic reductions in CO2 emissions andrunning costs can be attained compared with conventional boiler systems. The system allows thepractical application of heat pumps in cold regions such as northern Europe by introducing an
advanced refrigerant control system that realizes a hot water discharge temperature of 58°C
even at an ambient temperature of -20°C.

|1. Introduction
In Europe, the basic style of domestic heating is whole-building and around-the-clockheating where hot water produced by a heat source unit is re-circulated to heat dissipation
appliances such as radiators, which is different from the Japanese heating style. Natural gas andother fossil fuel-fired boilers have been the mainstream heat sources.
Due to increases in the prices of crude oil and natural gas, the risk of ensuring a supply ofnatural gas and the recent upsurge in concern about environmental issues, however, new heatsource units that have the potential to reduce CO2 emissions by utilizing an electric heat pumpsystem are in the spotlight.
As such, with European heat pump manufacturer NIBE, MHI has jointly developed achilled/hot water supply system for air conditioning and hot water supply appliances based onconventional air conditioning systems (air to water heat pump). This paper introduces an overview
and the features of the air to water heat pump for European domestic use.

|2. Overview of Product System
Figure 1 shows an overview of a system using this product. Hot water pipes for heating andhot water supply are connected to the indoor unit.
The unit can use fan coils and radiators as the heat dissipation appliances, which require
relatively high temperature water discharge, as well as floor heating appliances that use lowtemperature water discharge. It can be controlled for either appliance or for several appliances
simultaneously requiring different water temperatures. In addition, the chilled/hot water system for*1

Air-Conditioner Designing & Engineering Department, Air-Conditioning & Refrigeration Systems Headquarters*2

Nagoya Research & Development Center, Technical & Innovation Headquarters*3

Group Manager, Air-Conditioner Designing & Engineering Department, Air-Conditioning & Refrigeration Systems Headquarters*4

Engineering Manager, Air-Conditioner Designing & Engineering Department, Air-Conditioning & Refrigeration
Systems Headquarters

Mitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)3

air conditioning has a target temperature control system that can be changed according to theambient temperature and realizes highly efficient operation by adjusting the optimum watertemperature depending on the load.
The indoor unit has an integrated hot water storage tank and can be operated whileautomatically switching the water flow in response to the air conditioning requirements and theoccurrence of water heating load. The hot water tank is equipped with an auxiliary heater (9kW) so
that the heater can be used not only for hot water supply, but also as a heat source in the case of atemporary capacity shortage due to an abrupt increase in heating load (Figure 2).
Instead of an auxiliary heater, other exterior heat sources such as solar water heaters or
boilers can be combined, allowing the flexible construction of an individual heating systemdepending on customer use including required heat load and heat source, etc., all of which
contribute to the reduction of energy costs.

Figure 1 Overview of system
The system can use fan coils, radiators and floor heating. It can also handle sudden increases in hot water load
through the use of a built-in storage tank.

Figure 2

Examples of water flow control by operation mode

There are three water flow control mode options:(1) Heating load is covered only by the capacity of the heat pump, (2) Capacity shortage because of heating
overload, and (3) Water flow switching because of occurrence of water heating load.
When additional increases in both heating load and hot water supply load occur simultaneously, the systemswitches between modes (1) and (3) as appropriate.

|3. Overcoming Technological Difficulties
Because air-to-water heat pumps for water heating systems differ from conventional air
conditioners in terms of operating conditions and environment, a review of the main components
and control system can realize a hot water discharge temperature of 58°C even at an ambientMitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)
4

temperature of -20°C. The adoption of the same platform for the air conditioning heat source as isused in conventional systems – which have an abundant record of use – facilitates the common useof components and improves the marketability and reliability of the product (Figure 3). The items
modified from conventional air conditioners are described below.

Figure 3(1)

Improvements to outdoor unit

High compression-ratio operation control by liquid refrigerant back operation control
Since the ambient temperature can fall to about -20°C in northern and inland areas ofEurope, it is necessary for heating equipment to be able to maintain stable operation with water
discharged at a high temperature even at low ambient temperatures.
In a conventional air conditioner, the temperature of the air discharged inside of a roomneeds to be more than 40°C to avoid cold drafts, so that in this condition there needs to be about
2.5MPa in high pressure for the compressor (the pressure at condensation saturation
temperature). In an air-to-water heat pump for hot water heating use, on the other hand, a higher
water temperature is needed depending on the type of radiator, such that during hot watersupply operation, a water discharge temperature of up to about 60°C is required. At that timethe maximum required high pressure is about 3.8MPa, which is higher than that of aconventional system.
To increase the high pressure under a low ambient temperature, it is necessary for thecompressor to be operated under a high compression ratio. A gas refrigerant, on the contrary,
has the property that when adiabatically compressed at a high compression ratio, thetemperature of the refrigerant gas rises. Accordingly, the operation of a compressor with a highcompression ratio will likely cause refrigerant oil to degrade and the motor magnet todemagnetize, etc., which can substantially affect the reliability of the system (Figure 4).

Figure 4 Refrigerating cycle chart at low ambient temperature

The red line shows that the gas discharge temperature crosses a threshold in the caseof high-pressure-difference operations, the blue dashed line shows how to avoid thegas discharge temperature using the conventional control and the solid line shows
the new control.

Mitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)5

In a conventional air conditioner system, to prevent the discharge temperature of therefrigerant from the compressor from exceeding the limiting temperature in the case of anambient temperature drop, operations are conducted while restraining the high pressure andcompression ratio by reducing the rotational frequency of the compressor; thus, the temperatureand the amount of water supplied can decline when operating at a low ambient temperature if
the protective control adopted for the conventional air conditioner is applied to the air to water
heat pump. Therefore, in this product, modified controls in which the temperature of thedischarged refrigerant gas is controlled to be less than the limiting temperature by returning theliquid refrigerant to a compressor to cool therein are adopted, aiming to prevent a reduction in
the capacity of the compressor and maintain stable operations for hot water supply in cold
regions.
In order to achieve the above controls, a certain level of compressor durability is required
to facilitate high-compression-ratio operation while sucking the liquid refrigerant, which is notexperienced in a conventional air conditioner (Figure 5).
To determine the suitability of the compressors used in conventional air conditioners,
studies were carried out to determine whether the loads applied to the sleeve of the bearing andthe blade portions are within the design criteria under operating conditions, i.e., a hot water
discharge temperature of 58°C and an ambient temperature of -20°C, which is the lowest
service condition. As a result, it was ascertained that since the compressor can be used underhigh-compression-ratio operations on the basis of the specifications, a durability test was
conducted as additional verification and the progress of the wear of the blade and bearing
portion was observed.
In comparison with the durability tests of conventional air conditioners, major differencesin the amounts of wear between the two sets of test data were not seen (Figure 6), nor was the
progress of wear from the start of operations observed. This showed that a conventional
compressor can have equivalent durability even under high-compression-ratio operations andcan be applied to a heat pump for hot water heating. As a result, stable high-temperature water
discharge operation in cold regions was validated.

Figure 5
Operating range of compressor in conventional air
conditioner and predicted service conditions in new productFigure 6 Correlation between compressor durability elapsed time andamount of wearMitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)
6(2)

Optimization of defrosting operations
In the indoor heat exchanger of an air to water heat pump, water and refrigerant are heatexchanged, making it important for defrosting operations during heating or cooling operations
that due consideration be given to the freezing and breakage that arise from the drop in watertemperature. Particularly in defrosting operations at a low ambient temperature, the lowpressure of an indoor heat exchanger (the pressure at evaporation saturation temperature)
declines, increasing the risk of freezing.
In this product, to avoid the freezing of circulation water, the compressor speed and theopening of the expansion valve are controlled so that the water temperature and low pressure
will reach the appropriate level. When there is a risk of a decline in the water temperature andlow pressure because of a shortfall in the heat source due to a defrosting operation, the waterflow is switched to ensure the heat source so as to employ the heat accumulated in the hot watertank, preventing the freezing of the water heat exchanger.
(3) Modifying characteristics of expansion valve
In operations at a low ambient temperature, the evaporation temperature of the refrigerant
in the evaporator declines, decreasing the amount of circulated refrigerant. To achieve
high-compression-ratio operation with a small circulation amount, it is necessary to narrow the
opening of the expansion valve and fine control of the range of the narrow valve opening isnecessary. In a conventional expansion valve, however, the resolution of the valve in the rangeof the narrow opening is large, resulting in concerns about significant fluctuations in operating
conditions with each pulse action.
As a result of modifying the characteristics of the expansion valve and enhancing thecontrol resolution in the range of the narrow valve opening, stable operation is realized even in
high-compression-ratio operations, where the amount of circulated refrigerant is small.
(4) Reduction of amount of refrigerant
R410A is used as the refrigerant in the product. It is widely adopted in residential air
conditioners in Europe and is the same refrigerant used in conventional air conditioners.
R410A is a refrigerant that is subject to control by European refrigerant regulations
enacted in 2006, however, so it is desirable to reduce the load by as much as possible inconsideration of environmental factors. Moreover, in the case of systems enclosing more than
3kg of refrigerant, checks for refrigerant leaks must be carried out once every year, which
contributes to increased user expense and running costs.
In view of the above situations, by re-designing the length of the pipes to eliminate theneed for additional charging on site, the initial amount of enclosed refrigerant was reduced toless than 3kg for two models, reducing user expense.

|4. Comparison of Running Cost Advantages
High efficiency has been attained by using the same platform as MHI’s conventional air
conditioner for the outdoor unit and optimizing the control for the expansion valve. This allows the
FDCW100VNX system to secure one of the industry’s best COPs (Coefficient of Performance;
expressed by Output Capacity divided by Electric Power Consumption), in which at the rated
capacity (9kW), the COP is 3.60 for hot water discharged at 45°C and 4.44 for hot water
discharged at 35°C.
However, in order to make a contribution to reducing user energy costs, not only is the COPat the rated conditions important, but so is efficiency throughout the year. Thus, a trial calculationof the running cost advantage in the case of replacing an existing gas boiler with MHI’s heat pump
(HMA100V+FDCW100VNX) was conducted, validating the cost reduction effect. Under standard
European climate conditions1 (Strasbourg; Figure 7) and assumed annual loads of 28,000kWh, therunning cost of an existing boiler under continuous use is about 1,940 euro versus that of a heatpump of about 1,100 euro, resulting in an expected reduction in the running cost of about 840 euro
per year (Table 1)2.

Mitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)
7

Figure 7 Occurrence time ofambient temperature in
average European climate(Strasbourg)

Table 1Heat pump +auxiliary heaterGas boiler

Amount of energy used
(kWh/year)
10,024(9,142+882)
40,000Comparison of running cost
Energy unit cost(euro/kWh)

Running cost(euro/year)

Cost advantage(euro/year)

0.10991,102842

0.0486

1,944-

Calculation conditions
 Required annual capacity: 28,000 kWh (including hot water supply: 200 L/day)
 Gas boiler efficiency: 70%
 Ambient temperature conditions: standard European climate conditions (Strasbourg; Figure 7)
 Water discharge temperature: 45°C (EN14511 standard water discharge conditions) Energy unit cost: Standard price in France used2

In this trial calculation, loads at temperatures below -1°C surpass the capacity of the heatpump (Figure 8), so a built-in heater starts to work to compensate for the shortfall in the heatsource. The use of the electric heater may be a factor in the worsening of efficiency, but the
proportion of the auxiliary heat source to the required overall capacity is only about 3% annually(Figure 9), which is not a significant drag on annual efficiency. In addition to an electric heater as
an auxiliary heat source, an existing boiler may be used to further reduce the running cost, allowing
flexible designs according to customer requirements.

Figure 8 Heat pump capacity and required load assuming hot
water discharge operation of 45°C
Required loads are assumed under standard European climate conditions andannual required loads of 28,000 kWh.

Mitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)8

Figure 9

Annual heating output by heat source

Required load value for ambient temperatures over 16°C designates the total valueof hot water supply load at ambient temperatures over 17°C.

|5. Field Tests
To validate product reliability, field tests were carried out at eight locations in Europe incollaboration with NIBE (Figure 10). As a representative example, the case of Östersund in the
middle of Sweden (item (1) in Figure 10) is introduced here. The field test was conducted at aselected normal house with a total floor area of 200m2 and using radiators as heat dissipation
appliances (Figure 11).

Figure 11 Field test site at Östersund (coldregion)Floor Area: about 200m2, Number of Residents: 2,
Heating System: Radiators, Assumed Annual Heating
Load: about 32,000kWh

Figure 10 Field test locations

Cold regions: 2 locations, Normal regions: 5 locations,
Warm regions: 1 location

The actual data with respect to the temperature transition of the water supplied by heat pump
operation are shown in Figure 12. In the figure, temporary drops in water temperature indicate
defrosting operations.
The hot water discharge temperature is controlled at around 40°C in relatively high ambient
temperature zones in the daytime, but as can be seen, targeted hot water discharge temperatures
increase as the ambient temperature decreases. In this manner, optimizing the targeted temperaturein response to the change in load allows effective operation to be realized.
Field tests have continued since 2008 and have validated the air-to-water heat pump isutilized as a stable and useful heat source in user homes even in cold regions of Europe.

Mitsubishi Heavy Industries Technical Review Vol. 48 No. 2 (June 2011)
9

Figure 12

Transition of ambient temperature and water temperature

The targeted water temperature is automatically regulated depending on the ambient
temperature, so that the outlet temperature rises during the night when the ambient
temperature drops.

|6. Conclusion
With the collaboration of NIBE, one of the leading manufacturers of heat pumps in Europe,
MHI has developed a lineup of three models of heat pump systems of 8, 9 and 16kW and entered
the home heat pump market in Europe, which is expected to expand for the foreseeable future.
While the outdoor unit seeks to share the components of a conventional air conditioner, thecomponents and control system necessary under new service conditions are being reviewed andmodified to enhance product marketability.
We will continue to develop and provide new heat pump systems with high efficiency andhigh temperature water discharge that can be accepted by the heating cultures of cold regions
according to market needs.

References
1.
2.

ECEEE, http://www.eceee.org/Eco_design/products/boilers/
Europe’s Energy Portal, http://www.energy.eu/