KANEKA OLED Lighting Module SL(LE-01L, LE-02L, LE-03L, LE-01H, LE-02H, LE-03H)

Instruction Manual

Safety Information
1 Product Overview
2 Connections and Wiring (when dimming is required)
3 Connections and Wiring (when dimming is not required)
4 Installing Lighting Module SL
5 Appendix/Technical Specifications

p. 2
p. 6
p. 9
p. 25
p. 29
p. 36

To customers and dealers (installers):
 Thank you for purchasing this Kaneka product.
 When using this product be sure to follow the terms of use and safety
precautions in this manual. Kaneka shall bear no responsibility for damage
that occurs due to the product being used in a way that deviates from thecontents of this manual and the safety precautions below.
 Kaneka shall bear no responsibility for the installation of this product.
Installation shall be carried out under the responsibility of the dealer(installer). Contact the dealer (installer) about replacement parts.
To dealers (installers):
 After installing the product explain the safety precautions to the user andhand over this instruction manual.
 When installing the product etc. be sure to follow the instructions in thismanual.

Safety Information
OLED module is to be supplied by an isolating power source of appropriate voltage and current
limits. The intended DMX, DALI signal shall also be Class 2 type.
Be sure to read the cautions described here to prevent injury, malfunction, fire and similar.

Warning
CautionNot observing the cautions indicated by this symbol may cause
death or serious injury.
Not observing the cautions indicated by this symbol may causelight injury or property damage.

Be sure to follow the instructions indicated by the following symbols.
Indicates that you must not
perform the indicated task.

Indicates that you must performthe indicated task.

Warning
Ask installers to carry out installation or de-installation work.
Otherwise this may cause fire, electric shock, or injury if the product falls.
Installation and de-installation of the module requires expert knowledge and skill, so ask
installers to carry out the work.
Do not do the following.






Go near the module when it is hot
Forcedly bend, twist or pull on the module
Place heavy objects on the module
Bundle up Lighting Module SL, harnesses, etc.
Secure the module with staples etc.

Otherwise this may cause module malfunction, short circuits, or electric shock.
Do not wash with water, dismantle, or modify the module.
Otherwise this may cause fire, electric shock, or malfunction.
Do not place, use, or store the module in an area where water may drip on it, orcondensation may form. Do not touch the module with wet hands.
Otherwise this may cause electric shock, short circuits, or malfunction.
Do not cover with paper or cloth, or place the module near these and other flammableobjects.
Otherwise this may cause fire or burns.
Do not install, remove, or clean the module while it is turned on.
Otherwise this may cause electric shock or malfunction.
Do not touch, plug in or unplug the electric supply parts while the module is turned on.
Otherwise this may cause electric shock or malfunction.
2

Make sure that dirt, dust, or foreign objects do not collect on the connectors.
If dirt, dust, or foreign objects collect on the module this may cause fire, electric shock, or
malfunction.

CautionThis product contains glass. Do not drop the product, hit it with objects, push it
forcefully, or place heavy objects on it.
Otherwise this may cause damage or injury.
Do not suddenly heat or cool the module.
Otherwise this may cause malfunction or damage.
Do not use organic solvents, or any alkaline, strong acidic, or chlorinated detergents
when cleaning the module.
Otherwise this may weaken the module, causing damage or electric shock. It may also
cause discoloration.
Clean with a soft dry cloth.
For stubborn stains, gently wipe the stained area with a well wrung soft cloth moistenedwith diluted neutral detergent, and then finish with a soft dry cloth.
Do not directly touch the connectors and other metal terminals.
Otherwise this may cause malfunction.
Do not touch the module while it is lit or immediately after it is turned off.
The module may be hot when lit or immediately after it has been turned off, and may causeburns.
Inspect the module periodically.
Using the module for a long time without inspection may occasionally cause fire or electric
shock.
This product has a limited service life. After the product has been installed for 10 years, theinternal structure will have deteriorated even if it looks normal externally. If any problems
are discovered during inspections, or if 10 years have passed since the module wasinstalled, we recommend replacing it. Consult with the installer about what is covered by
the inspections.
Secure the module correctly for use.
If the module is not correctly secured, it may fall due to vibration, impact, earthquake, etc.,
and hit people, animals, plants, or property causing injury or damage.
Use the specialized harnesses when connecting the product. Be sure to use a
specialized dimming interface if you are using a dimming interface.
Not using the specialized harnesses and dimming interfaces may cause malfunction.

3

IMPORTANT SAFETY INSTRUCTIONS-SAVE THESE
INSTRUCTIONSDANGER-TO REDUCE THE RISK OF FIRE OR ELECTRICSHOCK, CAREFULLY FOLLOW THESE INSTRUCTIONS
If the shape of the plug does not fit the power outlet, use an attachment plug adaptor of theproper configuration for the power outlet.
This device complies with part 15 of the FCC Rules. Operation is subject to the following two
conditions: (1) This device may not cause harmful interference, and (2) this device must accept
any interference received, including interference that may cause undesired operation.
FCC CAUTION
Changes or modifications not expressly approved by the party responsible for compliance could
void the user’s authority to operate the equipment.
Note: This equipment has been tested and found to comply with the limits for a Class B digital
device, pursuant to part 15 of the FCC Rules. These limits are designed to provide reasonable
protection against harmful interference in a residential installation. This equipment generates,
uses and can radiate radio frequency energy and, if not installed and used in accordance with
the instructions, may cause harmful interference to radio communications. However, there is no
guarantee that interference will not occur in a particular installation. If this equipment does cause
harmful interference to radio or television reception, which can be determined by turning theequipment off and on, the user is encouraged to try to correct the interference by one or more of
the following measures:-Reorient or relocate the receiving antenna.
-Increase the separation between the equipment and receiver.
-Connect the equipment into an outlet on a circuit different from that to which the receiver isconnected.
-Consult the dealer or an experienced radio/TV technician for help4

Other cautions
 Static electricity may cause damage or malfunction. Be sure to remove static electricity fromthe product and the person handling it (person performing work).
 When cleaning the product do not polish it using cleanser or a scrubbing brush. Otherwise
this may cause scratches and corrosion.
 The product is incombustible. Follow municipal regulations when disposing of the module.
 The OLED panel cannot be replaced by itself. If it needs replacing, the whole Lighting
Module SL must be replaced.

5

1

Product Overview

This lighting module contains an organic EL lighting panel (OLED).
It is referred to as Lighting Module SL in this manual.

Lighting Module SL
The lineup is as follows.
●Normal type
Model Number

Color Temperature

LE-01L

3000K

LE-02L

3000K high color rendering

LE-03L

4000K high color rendering●High luminance type
Model Number

Color Temperature

LE-01H

3000K

LE-02H

3000K high color rendering

LE-03H

4000K high color rendering
If you are linking Lightning Module SL, use the same types. Do not mix the normal
type and the high luminance type.

6

Accessory List
The specialized accessories for this product are as follows. Be sure to use specialized
accessories.
Type

Name

Installation
bases

Installation Base S
Installation Base A

Allows the module to be installed on asurface either in front of or behind the lightemitting side

Dimming
interfaces

PWM Dimming Interface

Use for PWM dimming

DALI/DMX Dimming Interface

Use for DALI/DMX dimming-

Power unit

Harnesses*:

Main specifications, etc.
Allows the module to be installed on asurface behind the light-emitting side

MEAN WELL PLC-100-24

Linking harness

Used to connect Lighting Module SL
togetherConversion harness

Used for the following: Connecting the Lighting Module SL to theextension harness
 Connecting the Lighting Module SL to thepower harness

Extension harness

Used for the following: Connecting the conversion harness to thedimming interface
 Connecting the conversion harness to theconnection harness
 Connecting the conversion harness to thebranch harness
 Connecting PWM dimming interfaces together

Branch harness

When used with the dimming interface,
increases the number of Lighting Module SL
that can be connected*

Connection harness

Used for the following: Connecting the power harness to theextension harness
 Connecting the power harness to thebranch harness

Used for the following: Connecting the DC output side of thepower unit to the dimming interface
 Connecting the DC output side of thePower harness
power unit to the conversion harness
 Connecting the DC output side of thepower unit to the connection harness
The branch harness alone cannot be used to increase the number of connections.
The power cable to be connected to the AC IN of the power unit should be provided
by the dealer (installer).

7

Part Names
Light-Emitting Side of Lighting Module SL

Front case

OLED panel

Back of Lighting Module SL
Back case

Channel switch
DC connector 1

DC connector 2
Product serialNo.label

DC connectors 1
and 2

Connect the conversion or linking harness (when connecting another
Lighting Module SL). Connect to either connector 1 or 2.
The unused connector can be used to connect the linking harness of thenext Lighting Module SL when connecting multiple modules.

Channel switch

Select the channel from ch1 or ch2. Select the channel based on thechannel settings of the connected dimming interface.

 The channel switch is set to ch1 when shipped.
 It will not be possible to dim the lights correctly if the channel switch and dimming
interface channel setting do not match.
 When using a branch harness, the channel switch settings will be ignored, andthe channels set by each branch of the branch harness will be used.
 Use a thin flathead screwdriver, clip, or similar to switch the channel switch. Do
not use sharp pointed objects as they may damage the switch.

82Connections and Wiring (when dimming is required)
If dimming is not required refer to “3 Connections and Wiring (when dimming is not
required)”.

Wiring Overview
The power unit, dimming interface, Lighting Module SL etc. should be connected as shown below.
 The length of the wiring may cause the voltage to drop. Make sure that the wiring is the sameor shorter than the lengths indicated in the connection diagrams.
 The number of Lighting Module SL that can be connected to one power unit differs dependingon the connection method used. Refer to "Maximum number of Lighting Module SL that canbe connected (with dimming)".
 Be sure to use the specialized harnesses to connect the modules.
When wiring leave enough leeway so that excessive force is not placed on the harness
cables and connectors. Placing excessive force on the cables or connectors may
cause damage or malfunction.

●When using PWM dimming or DALI/DMX dimming with no branching

To the dimmer/network/
controller, etc.

Power harness

Dimming
interface

Extension
harness

Conversion
harness

Power unit

Lighting Module SL

PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

Linking harness
4.5m or 3.5m *2

13.0m *1

*1: The wiring lengths indicated in the diagram above do not include the length of the dimming
interface.
*2: The maximum length for the normal type is 4.5m, and 3.5m for the high luminance type.

9

●When using PWM dimming with branching and one dimmer
Dimming cable *2

Power harness

Dimming
interface

To the dimmer,
controller, etc. *2

Conversion harness
Branchharness *1

Power unit

Extension
harness

Extension harness (0.2m)

Lighting Module SL
PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

Linking harness
PWM
CH

1
2

PWM
CH

1
2

4.0m or 3.5m *4

13.2m *3

*1: The channels are decided based on the branch connected to, regardless of the Lighting Module
SL ch settings.
*2: Connect the dimmer to one of the PWM dimming interfaces, and connect the PWM dimming
interfaces with a dimming cable.
The dimming cable should be provided by the dealer (installer).
*3: The wiring lengths indicated in the diagram above do not include the length of the dimming
interface or branch harness.
*4: The maximum length for the normal type is 4.0m, and 3.5m for the high luminance type.

●When using PWM dimming with branching and two dimmers
Conversion harness
To the dimmer, controller, etc. *2
Power harness

Branchharness *1

Dimming
interface

Power unit

Extension
harness

Extension harness (0.2m)

Lighting Module SL
PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

Linking harness
PWM
CH

1
2

PWM
CH

1
2

4.0m or 3.5m *4

13.2m *3

*1: The channels are decided based on the branch connected to, regardless of the Lighting Module
SL ch settings.
*2: Connect a dimmer to each of the two PWM dimming interfaces.
*3: The wiring lengths indicated in the diagram above do not include the length of the dimming
interface or branch harness.
*4: The maximum length for the normal type is 4.0m, and 3.5m for the high luminance type.

10

●When using DALI/DMX dimming with branching

To the dimmer, controller, etc.
Power harness

Dimming
interface

Conversion harness
Lighting Module SL

Branchharness *1

Power unit

PWM
CH

Extension
harness

1
2

PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

Linking harness
PWM
CH

1
2

PWM
CH

1
2

4.0m or 3.5m*3

13.0m *2

*1: The channels are decided based on the branch connected to, regardless of the Lighting Module
SL ch settings.
*2: The wiring lengths indicated in the diagram above do not include the length of the dimming
interface or branch harness.
*3: The maximum length for the normal type is 4.0m, and 3.5m for the high luminance type.

Maximum number of Lighting Module SL that can be connected (with dimming interface)
When using dimming interface the maximum number of Lighting Module SL that can beconnected is as follows.
Model number
LE-01L, LE-02L, LE-03L
LE-01H, LE-02H, LE-03H

Branch harness

Max. no. per branchMax. no.

Not used

-

10

Used

9

18 (9 + 9)

Not used

-

8

Used

8

16 (8 + 8)

11

Connecting the Power Unit
Refer to the power unit instruction manual for details.

1Remove the ‘AC IN’ and ‘DC OUT’ covers from the power unit

2

Connect the power cable to ‘AC IN’

Slide in the direction indicated by the arrows to remove the covers.

Use a flathead screwdriver to loosen the terminal screw, insert the power cable so thepolarity is correct, and tighten the terminal screw to secure the power cable.
Make sure that you do not forget to loosen and tighten the screw.

N

L The power cable to be connected to the AC IN of the power unit should be
provided by the dealer (installer).
 Connection to the AC IN of the power unit must be performed by a qualified
electrician.

123Connect the power harness to ‘DC OUT’Use a flathead screwdriver to loosen the terminal screw, insert the power harness so thepolarity (BK: -V, WT: +V) is correct, and tighten the terminal screw to secure the power
harness.

-V

4

+V

Reattach the ‘AC IN’ and ‘DC OUT’ covers
Before reattaching the covers, make sure that no wires are sticking out of the power
unit, and that the right and left wires are not touching. If the wires are sticking out or
the right and left wires are touching, rewire the connections.

13Connecting Dimming Interfaces
Connect the PWM dimming interface or DALI/DMX dimming interface according to the type of
dimming required.

Dimming Interface Part Names●PWM Dimming Interface
・FrontPWM input/feed
terminal

Power input
connector

Power on indicator
OLED output
connector

・Back
Dimming characteristic
switches

14

●DALI/DMX Dimming Interface
・FrontDALI dimming signal
terminal block

Power input
connector

DMX input
dimming signal
connector
DMX feeddimming signal
connector

OLED output
connector

Power on indicator

・BackMode setting
switches(same for
DALI/DMX)

DMX address
selection
switches15

Connecting Dimming Interfaces (for PWM dimming)
If you wish to use PWM dimming: Use the PWM dimming interface and connect to a PWM dimmer.
Use a commercially available PWM dimmer that conforms to JISC8120 or IEC60929.

1

Connect the power harness connected to the power unit to the power
input connector
Be sure to insert the connector facing the right way, until it is secured by the tab.

Power harness

2

Connect the extension harness to the OLED output connector

Be sure to insert the connector facing the right way, until it is secured by the tab.

Extension harness

When using a branch harness, two PWM dimming interfaces must be used. Proceed tostep 3 and connect two PWM dimming interfaces. When not using a branch harness
proceed to step 6.

16

3Connect the extension harness connected to the first PWM dimming
interface to the power input connector of the second PWM dimming
interfaceBe sure to insert the connector facing the right way, until it is secured by the tab.

Extension harness

4

Connect the branch harness to the OLED output connector of thesecond PWM dimming interface
Be sure to insert the connector facing the right way, until it is secured by the tab.

Branch harness

5 Connect an extension harness to the end of each branch of the branchharness
Be sure to insert the connector facing the right way, until it is secured by the tab.

17

6 Connect the dimming signal cable of the PWM dimmer to the PWM
input/feed terminal

Use a flathead screwdriver to loosen the terminal screw, check that the dimming signal
input and output are correct, and insert the signal cable from the dimmer. Tighten theterminal screw to secure the signal cable.
When using a branch harness it is necessary to either connect a dimmer to each of thePWM dimming interfaces, or connect a dimmer to one PWM dimming interface andconnect the interfaces with a dimming cable. Refer to "2 Connections and Wiring (whendimming is required)" (p.10).
Refer to the instruction manual for the PWM dimmer you are using for more details about
connecting the PWM dimmer.
PWM input/feed terminal

7 Set the dimming characteristic switches on the dimming interface
according to the construction specifications
Refer to "PWM Dimming Interface Settings and Dimming Characteristics" in "5
Appendix/Technical Specifications" for the dimming interface settings.

18

Connecting Dimming Interfaces (for DALI/DMX dimming)
If you wish to use DALI or DMX dimming: Use a DALI/DMX dimming interface and connect to a
DALI network or DMX controller.
The DALI/DMX dimming interface can be used for both DALI and DMX, but the connectors used
to connect the cables differ.

1 Connect the power harness connected to the power unit to the power
input connector
Be sure to insert the connector facing the right way, until it is secured by the tab.

Power harness

2 Connect the extension harness or branch harness to the OLED output connector
Be sure to insert the connector facing the right way, until it is secured by the tab.

Extension harnessorBranch harness

3 When using a branch harness, connect the extension harness to thebranch harness
Connect an extension harness to the end of each branch of the branch harness.

19

4 Connect the DALI network/DMX controller signal cable●When using DALI dimming
Use a flathead screwdriver to loosen the DALI dimming signal terminal block screw, checkthat the dimming signal input and output are correct, and insert the signal cable from the
DALI network. Tighten the DALI dimming signal terminal block screw to secure the signal
cable.
Use devices that conform to IEC62386-207 for the DALI network. Refer to the instruction
manual for the DALI device you are using for more details about connecting to a DALI
network.
DALI dimming signal terminal block●When using DMX dimming
Connect the cable to the DMX controller to the DMX input dimming signal connector and
DMX feed dimming signal connector on the dimming interface. Use a commerciallyavailable DMX controller that conforms to DMX512/1990. Refer to the instruction manual
for the DMX controller you are using for more details about connecting to a DMX controller.
DMX input dimming signal
connector

DMX feed dimming signal
connector

5 Set the dimming interface according to the specifications of thedimming method being used

Refer to "DALI/DMX Dimming Interface Settings and Dimming Characteristics" in "5
Appendix/Technical Specifications" for the dimming interface settings.

●When using DALI dimming
Set the mode setting switches (same for DALI/DMX) according to the specifications of theconnected DALI network.
●When using DMX dimming
Set the mode setting switches (same for DALI/DMX) and DMX address selection switches
according to the specifications of the connected DMX controller.
20Connecting Lighting Module SL
Connect the conversion harness connected to Lighting Module SL and the extension harness
connected to the dimming interface.
Alternatively, if you are linking multiple Lighting Module SL, use the specialized linking harness
to connect them. The maximum number of Lighting Module SL that can be linked and used differs
depending on whether the branch harness and dimming I/F is used.
If you are linking Lightning Module SL, use the same types. Do not mix the normal
type and the high luminance type.

1

Connect the Lighting Module SL side connector of the conversion
harness to the DC connector on Lighting Module SL

Connect to either DC connector 1 or 2. Choose depending on the installation position andwiring.
The connector is polarized, so ensure that pin 1 (marked with △) is oriented as shown inthe diagram before connecting.

21

2

To link multiple Lighting Module SL, connect one of the linking
harness connectors into the empty DC connector

3Connect the other linking harness connector to the DC connector of
the next Lighting Module SL

22

Make sure that the linking harnesses connected to Lighting Module SL do not crossover each other when the modules are installed on a wall, etc. If they cross over eachother, change how the linking harnesses are connected.

The harnesses crossover each other.
Switch the linking
harnesses over so thatthey do not cross overeach other.

4

Repeat steps 2 and 3 until all Lighting Module SL are linked

5

Connect the extension harness to the extension harness sideconnector of the conversion harness.

When using a branch harness, link the Lighting Module SL to be connected to the otherbranch in the same way.

When using a branch harness, connect the extension harness and conversion harness tothe other branch in the same way.

Extension harness

Conversion harness

23

Disconnecting the Conversion and Linking Harnesses
To disconnect the connectors of the conversion or linking harnesses connected to Lighting
Module SL, press the release buttons on the sides of the connector and pull the connector out
as shown below.

 Do not try to pull out the connector without pressing the release buttons, or bypulling on the cables. Otherwise this may cause damage or malfunction of theharnesses and Lighting Module SL.
 Hold the connector part of the linking harness when attaching or removing it.
Holding any part other than the connector may cause the connector to bedamaged (e.g. the connector may come off).

24

3Connections and Wiring (when dimming is not required)

Wiring Overview
The power unit and Lighting Module SL etc. should be connected as shown in the diagram below.
 The length of the wiring may cause the voltage to drop. Make sure that the wiring is the sameor shorter than the lengths indicated in the connection diagrams.
 The number of Lighting Module SL that can be connected to one power unit differs dependingon the connection method used. Refer to "Maximum number of Lighting Module SL that canbe connected (without dimming)".
 Be sure to use the specialized harnesses to connect the modules.
When wiring leave enough leeway so that excessive force is not placed on the harness
cables and connectors. Placing excessive force on the cables or connectors may
cause damage or malfunction.

●With no branching

Power harness

Conversion
harness
Connection
harness *1

Extension
harness *1

Lighting Module SL
PWM
CH

1
2

PWM
CH

1
2

PWM
CH

1
2

Power unit
Linking harness
13.0m *2

6.5m or 4.5m *3*1: If no extension harness is used the connection harness and extension harness can be omitted.
Connect the power harness to the conversion harness.
*2: The wiring lengths indicated in the diagram above do not include the length of the connection
harness.
*3: The maximum length for the normal type is 6.5m, and 4.5m for the high luminance type.

25

●With branching
Extension
harness

Branchharness

Conversion
harness

Lighting Module SL
PWM
CH

PWM
CH

1
2

1
2

PWM
CH

1
2

PWM
CH

1
2

Power harness
Connection
harness

Linking harness

Power unit
PWM
CH

13.0m *1

PWM
CH

1
2

1
2

3.0m or 2.0m *2*1: The wiring lengths indicated in the diagram above do not include the length of the connection
harness or branch harness.
*2: The maximum length for the normal type is 3.0m, and 2.0m for the high luminance type.

Maximum number of Lighting Module SL that can be connected (without dimming)
When not using dimming the maximum number of Lighting Module SL that can be connected is
as follows.
Model number
LE-01L, LE-02L, LE-03L
LE-01H, LE-02H, LE-03H

Branch harness

Max. no. per branchMax. no.

Not used

-

14

Used

7

14 (7 + 7)

Not used

-

10

Used

5

10 (5 + 5)

26

Connecting the Power Unit
Connect the power cable and power harness to the power unit. Refer to “Connecting the PowerUnit” in “2 Connections and Wiring (when dimming is required)” when wiring.

Connecting Lighting Module SL
Connect Lighting Module SL to the power unit.
Alternatively, if you are linking multiple Lighting Module SL, use the specialized linking harness
to connect them. The maximum number of Lighting Module SL that can be linked and used differs
depending on whether the branch harness is used.

1

Follow steps 1 to 4 in “Connecting Lighting Module SL” in“2 Connections and Wiring (when dimming is required)” to connect
the required number of Lighting Module SL

2

When using a branch harness or extension harness, connect theharness as follows●When using an extension harness
As shown in the diagram, connect the connection harness and extension harness to the power
harness.

Power harness

Extension
harness

Connection
harness●When using a branch harness
As shown in the diagram, connect the connection harness, branch harness, and extension
harness to the power harness.

Power harness

Branchharness

Connection
harness27

Extension
harness

3

Connect the power harness or extension harness to the extension
harness side connector of the conversion harness.
Power harness or Extension harness

Conversion harness28

4Installing Lighting Module SL

Use the specialized installation bases to attach Lighting Module SL to a wall or ceiling.

Caution
Do not directly secure Lighting Module SL to walls etc. without an installationbase using screws, adhesive or tape.
Otherwise product performance may deteriorate, and the modules may become
damaged, or fall and cause injury.
When installing the modules protect hands by wearing gloves or similar.
Otherwise this may lead to cuts or other hand injuries.

Securing Installation bases
Installation Base Types
The following two types of installation base are available.
●Installation Base S

This base is 13/64"(5mm) thick when installed (including Lighting Module SL). It can beinstalled on a surface behind the light-emitting side.
When Lighting Module SL is set in installation base S, the base cannot be seen from the lightemitting surface of the module.
The types of screws that can be used for installation are limited. Use the screw shown below.
 Wood screw:： M3.1 x 25 mm
If a screw not listed above is used, the head of the screw will obstruct the product,
preventing it from being attached, tilting it, or causing scratches or other damage.

29

●Installation Base A

B

A

B

This base is 13/64"(5mm) thick when installed (including Lighting Module SL).
Depending on how installation base A is secured, the module can be installed on a surface
either in front of (using the A screw holes) or behind (using the B screw holes) the light-emittingside.
As the screws are attached outside of where Lighting Module SL sits, any 3.0 to 4.0 mm
diameter screws can be used.
 Use an appropriate screw length according to the construction material andthickness of the surface where the module will be installed.
 When using the base so that the module is installed on a surface in front of thelight-emitting side, it may be difficult to attach the SL Light Module after the basehas been attached. When installing in this kind of location, attach the SL Light
Module to installation base A first before installing the base.

30

Installing on a wall or similar

1

Secure the installation base using screws
Contact us beforehand if you wish to secure the module on a wall or other surface
where it cannot be directly secured using screws, such as a gypsum wall.

●Installation Base S

31

●Installation Base A
 To install on a surface behind the light-emitting side To install on a surface in front of the light-emitting side32

Attaching Lighting Module SL
Attach Lighting Module SL to the secured installation base.

1

Check the position of the grooves and the direction of the arrow on
the back of Lighting Module SL
Arrow that indicates the directionin which to slide the module when
attaching it

GrooveGroove2

Align the hooks on the installation base and the grooves on Lighting
Module SL, and attach the module to the installation baseView from the side
The illustration shows installation base S.

33

3

Slide Lighting Module SL to secure it in the direction indicated by thearrow on the back of the module
Slide it until you hear a click and it is secure.

View from the side
The illustration shows installation base S.
Lightly pull Lighting Module SL forward to check that all four of the grooves on theback of the module and hooks on the installation base are secure.

34

Removing Lighting Module SL
Follow the procedure below when removing Lighting Module SL for repair or to replace them.

1

Slide Lighting Module SL in the opposite direction to the arrow on theback of the module (the direction with a small protrusion), and release
the hooks on the installation base from the grooves on Lighting
Module SL
There is a small protrusion on the side where the arrow ison the back.
If you cannot check the direction of the arrow on the backof the module, use the protrusion on the side to confirm thedirection.

View from the side
The illustration shows installation base S.

2Pull Lighting Module SL forward to remove it
If it cannot be removed, the hooks on the installation base may not be fully released
from the grooves on the back of the module. Do not pull the module with excessive
force. Check that the module has been slid far enough that the hooks and grooves
have released.

35

5

Appendix/Technical Specifications

Harness List
The harnesses used to wire this product are as follows.
Be sure to use specialized harnesses.
Type

Appearance

Length1-31/32"(0.05m)
4-23/32"(0.12m)

Linking
harness

11-13/16"(0.3m)
19-11/16"(0.5m)

Conversion
harness

11-13/16"(0.3m)
7-7/8"(0.2m)
3'3"(1.0m)

Extension
harness

9'10"(3.0m)
16'5"(5.0m)
32'10"(10.0m)

Branchharness

7-7/8"(0.2m)

Connection
harness

7-7/8"(0.2m)

Powerharness

9'10"(3.0m)

36

PWM Dimming Interface Settings and Dimming Characteristics
Dimming Characteristic Switch Settings●ch settingch

Switchsetting
4

1

0

2

1

●Mode setting
Mode*1

Switchsetting

Input PWM

Output PWM

123
1

000

2

100

11 - 94% (A)
5 - 94% (B)3010

0 - 100% (C)4110

11 - 94% (A)5001

5 - 94% (B)6101

11 - 94% (A)7011

5 - 94% (B)8111

11 - 94% (A)

0 - 100%

0 - 58%0 - 50%0 - 42%*1 For the dimming characteristics for each mode, refer to "Dimming Characteristics for Each Mode
(PWM Dimming)" on the following page.

37

Dimming Characteristics for Each Mode (PWM Dimming)

38

DALI/DMX Dimming Interface Settings and Dimming Characteristics
Mode Switch Settings (same for DALI/DMX)●Terminator setting
Switchsetting

Terminatorsetting4

Disabled

0

Enabled1●Mode setting
Mode*1

Switchsetting

Input signal

No. of ch*2

Options*3

1ch(ch1 and ch2 are controlled
together)

None
Smoothing

2ch

None

123
1

000

2

100

3

010

4

110

5

001

6

101

7

011

8

111

DALI

(ch1 and ch2 arecontrolled separately)
2ch(ch1 and ch2 arecontrolled separately)

DMX

Smoothing
None
Smoothing
None
Smoothing*1 For the dimming characteristics for each mode, refer to "Dimming Characteristics for Each Mode
(DALI Dimming)" or "Dimming Characteristics for Each Mode (DMX Dimming)" on the following
pages.
*2 Select ch1 or ch2 on the channel switch on Lighting Module SL.
*3 You can select smoothing to enable smoother dimming.

DMX Address Selection Switch Settings (DMX only)ch1

Address set using the switchesch2Address set using the switches +1

39

Dimming Characteristics for Each Mode (DALI Dimming)

40

Dimming Characteristics for Each Mode (DMX Dimming)

41

NOTESNOTES

KANEKA OLED Lighting Module SL Instruction Manual
Document No. OBD-110-501/001
First edition, August 2017

Printed in Japan© Kaneka Corporation 2017
Duplication or modification of this content without permission from Kaneka Corporation is prohibited.
KANEKA CORPORATION
OLED Business Development Project
1-12-32, Akasaka, Minato-ku Tokyo 107-6028, Japan
TEL +81-3-5574-8009 FAX +81-3-5574-6161
email oled-market@kaneka.co.jp