Drawing No.

Rev.

WDT-6LR-Z2-W18

J

SPECIFICATIONS

Product Name: Wireless Data Acquisition SystemTransmitter
Model: WDT-4LR-Z2/WDT-5LR-Z2/WDT-6LR-Z2

Page

1/8

図番改訂ページ

WDT-6LR-Z2-W18

J

2/8

1．ModelContents

ＷＤ T－□LR－Ｚ２
Z2 Zigbee2007Pro 2.4GHz type
4 For LR4 Series Signal Tower
5 For LR5 Series Signal Tower
6 For LR6 Series Signal Tower
T Transmitter
WD Product Name: Wireless Data Acquisition System Series

2．General Specifications
Item
Connected model

WDT-4LR-Z2

Contents
WDT-5LR-Z2

WDT-6LR-Z2

LR4 Series Signal Tower
Body unit top attachment

LR5 Series Signal Tower
Body unit top attachment

LR6 Series Signal Tower
Body unit top attachment

Rated Voltage

24V DCOperating Voltage Range

19.0V DC～26.4V DC

Rated Current Consumption

Max.55mA

Operating Ambient Temperature-10℃～+50℃

Operating Ambient Humidity
Storage Ambient Temperature

85%RH or less, no condensation

Storage Ambient Humidity

85%RH or less, no freezing

Mounting Location

Indoor Only

Mounting Method

Upright-20℃ ～ +60℃

Protection Rating
IP 65 (IEC 60529), NEMA TYPE 4X,13
Environmental Conditions Based on LR4 Series Signal Tower Based on LR5 Series Signal Tower Based on LR6 Series Signal Tower
Insulation ResistanceMore than 5MΩ at 500VDC between live part and non-current carrying metallic partWithstand Voltage

500VAC applied for 1min between live part and non-current carrying metallic part without
breaking insulation

Mass
Outer Dimensions

70g±10g

74g±10g
Refer to the Outer Dimension Drawing

85g±10g

図番改訂

ページ

WDT-6LR-Z2-W18

J

3/8

Contents
WDT-5LR-Z2

WDT-6LR-Z2

3．Performance Specifications
3.1. Wireless Specifications
Item

WDT-4LR-Z2Telecommunication Protocols

IEEE 802.15.4 (Wireless Communications)

Communication Frequency

2405MHz - 2480MHz(16 channel)

Communication system

Direct Sequence Spread Spectrum (DS-SS)

Communication protocols

ZigBee2007 Conformity(original Profile lmplementation)

Transmitter Output

No more than 3mW (Depending on Antenna Access Point)

Communication distanceApproximately 30 m from source (reference value)※1

Japan, USA, Europe, Korea, Taiwan, Thailand, China, Mexico, Philippines,Vietnam, Canada, Malaysia, Singapore

Usable regions※2

External Contact Input

Control signal input

Number of Contacts

6 points (red, amber, green, blue, white, buzzer)

Input Reaction Time

100 ms or longer

Display Unit

Indicator for monitoring the status

Operation Unit

DIP switches※1 The radio transmission is dependent upon the environment and installed location.
Remarks※2 Please do not use any regions nor countries other than admitted regions
and countries. Failure to do so may come into conflict with the law.

4. Function Specifications
Item

Description

Signal Tower Transmission
Information

It is possible to select from 2 types of Immediate transmission mode andRequest transmission mode.

Immediate transmission mode

Send immediately after the status of the signal tower changes.

Request transmission mode

Send only after receiving a signal tower status request from the host PC.

Select Signal Tower
Information Format
Extended Format
Standard Format

It is possible to select from 2 types of Extended Format and standard Format.
Sets up six types of signal tower information.
Sets up five types of signal tower information.
(Format compatible with WDT-5E-Z2 and WDT-6M-Z2.)

図番

改訂

ページ

WDT-6LR-Z2-W18

J

4/8

5. Conformity Standards
Item

Description

WDT-4LR-Z2
Conformity Standards

Japan Radio Law (ARIB STD-T66 Conformity)※1
UL 508 ,CAN/CSA C22.2 No.14-18
FCC Part 15 Subpart B Class B, FCC Part15 Subpart C ※1
EN 62368-1,EN 55032 ClassB,EN55035
EN 62479, EN 300 328, EN 301 489-1, EN IEC 63000
RSS-247 Issue 2, ICES-003 Class B
KN 301 489-1/-17
NCC ※1NBTC TS 1035-2562
NOM-208-SCFI-2016, IFT-008-2015
MCMC MTSFB TC T007：2020
MEMORANDUM CIRCULAR NO. 03-05-2007
MEMORANDUM CIRCULAR NO. 01-02-2020

WDT-5LR-Z2
WDT-6LR-Z2
Conformity Standards

Remarks

Japan Radio Law (ARIB STD-T66 Conformity)※1
UL 508 ,CAN/CSA C22.2 No.14-18
FCC Part 15 Subpart B (Class B), Subpart C ※1
EN 62368-1, EN 55032 (Class B),EN55035
EN62479, EN 300 328, EN 301 489-1, EN IEC 63000
RSS-247 Issue 2, ICES-003 (Class B)
KN 301 489-1/-17
NCC ※1NBTC TS 1035-2562
NOM-208-SCFI-2016, IFT-008-2015
MCMC MTSFB TC T007：2014
MEMORANDUM CIRCULAR NO. 03-05-2007

・Conforms to the CE Requirements
・Conforms to the UKCA Requirements
・ UL/cUL Listed (File No.E215660)※1 Built-in certified wireless module図番改訂ページWDT-6LR-Z2-W18

J5/8[Handling Precaution]◆About handling this product・This product (including software) is shipped only after undergoing strict quality controls and inspections. However, should
you encounter any issues, please contact your PATLITE sales representative.
・This product (including software) is developed, designed and manufactured for general usage, such as office use,
personal use, standard industry, and other related systems. Do not use, either directly or indirectly, in applications where ahigh level of safety is required, such as medical equipment or where human life is involved. We shall not be held liable forany damages or losses, nor be held responsible for any claims by a third party, as a result of using this product.
・The suitability of this product in the system, with other machines and equipment, shall be tested and confirmed by thecustomer. We assume no responsibility regarding this. Design safety into the system to cope with misoperation, misuse,going offline, and other unforeseen operation of this product.
・We bear no responsibility for damages, lost opportunities, lost profits, compensation for accidents, or other costs
including but not limited to personnel, construction, transportation, and shipping costs, related to using this product. We
bear no responsibility for defects in other products, regardless of the other product's connection to this product (such as acommunication line), or for the cost of repairing damages, losses, defects, or recovering lost data related to using the otherproducts, including but not limited to personnel, construction, transportation, and shipping costs.
・To improve the functionality in the software for this product, we will update the software at our own discretion. We bear noresponsibility for the results of software updates, such as damages, lost opportunities, lost profits, compensation foraccidents, or other costs including but not limited to personnel, construction, transportation, and shipping costs, related tousing this product. We bear no responsibility for defects in other products, regardless of the other product's connection tothis product (such as a communication line), or for the cost of repairing damages, losses, defects, or recovering lost data
related to using other products, including but not limited to personnel, construction, transportation, and shipping costs.
・Note the following statements regarding the software for this product, which require prior written consent from PATLITE:＊Do not duplicate the software for this product.
＊Do not alter, combine, reverse-engineer, decompile, or disassemble the software for this product.
＊Do not license, rent, or resell the software for this product to a third party.
＊Do not store the software of this product on a network so it can be transmitted to a third party.
＊Do not remove the copyright notice or other trademark and company rights attached to the software for this product.
◆Things you should always do for your safety
・Do not disassemble or modify the product. Failure to do so may lead to product malfunction or cause fire or electrocution.
・Avoid spilling liquids (such as water or chemicals) into this product. Avoid dropping foreign metallic objects (such ascopper wire) into this product. Failure to follow these instructions could result in electric shock or equipment damage.
・Do not drop or hit this product. Failure to follow these instructions could result in electric shock or equipment damage.
・Do not apply too much force to switches and buttons on this product. Failure to follow this instruction could result inequipment damage.
◆Installation
・Turn off the power when wiring, inspecting, or repairing this product. Failure to follow this instruction could result inequipment damage.
・Do not install in locations near fire, or environments with high temperature and humidity. Do not install this product wherecorrosive or flammable gas is present.
・Do not install on an unstable surface. Failure to follow these instructions could result in injury or equipment damage.
・This product is rated for indoor use only. Please install and use this product indoors only.
・Avoid the following locations for installation of this product.
＊Places exposed to direct sunlight.
＊Places near fire or environments with high temperatures and humidity.
＊Environments where temperature changes are severe, and where there is condensation.
＊Environments with poor breathability and ventilation.
＊Places where external vibrations are directly transmitted to this product.
＊Environments where corrosive gas is present.
＊Locations exposed to salty sea air.
＊Locations near strong magnetic fields.
＊Environments where there is dust, iron powder, and so on.
＊Environments where chemicals and oil mist are present.
◆About maintenance・Do not clean this product with volatile chemicals such as benzine or thinners, or with chemical wiping cloths as it could
damage the product.
・Please clean this product with a soft, dry cloth.
・If the dry cloth is unable to clean off any dirt and grime, wipe the product firmly with a slightly water-moistened cloth.

WDT-6LR-Z2-W18

6/8

パトライト

株式会社
PATLITE Corporation

WDT-6LR-Z2-W18

7/8

パトライト

株式会社
PATLITE Corporation

WDT-6LR-Z2-W18

8/8

パトライト

株式会社
PATLITE Corporation