TPS Series
DIGITAL MULTI POWER METER

If you use this TPS multi-meter, you can measure 16 elements on the main display,and 21 elements on the sub-display.

TPI KOREA
www.tpikorea.com

TPS

Multi-Power meterFeaturePackage display (4 elements)
16 elements can be displayed on the screen.
High -speed digital operation system is adopted.
Many elements are displayed on real time 1 screen withthe combination by LCD display. Even when there isno lighting, it displays clearly with backlight.
The same attachment as 110 wide angle meter.
It possible to replace, since it is the same size (110type)
Various outputs.
Analog output 4 ~ 2 0 m A 1~5V max 3ch and pulse output(Wh or varh). Digital output (RS485).
Demand alarm relay output. ( Demand Amp. or Demand Watt)
It possible to measure 4 times rated current.
Also in consideration of inrush current, it possible to measure
up to 4 times of rated input current.

Specification
Measurement item
Current（ R, S, T ）Voltage（ R -S, S-T, T -R ）3Input range
0～5A （up to 20A)
0～150V or 0 ～300V(max 600V)

Active power

10～1k W or 0 ～2kW

Reactive power

1Power factor
Frequency

11LEAD 1kvar～ 0 ～ LAG1kvar
LEAD 2kvar～ 0 ～ LAG2kvar
LEAD 0 ～1～ LAG 045Hz ～65Hz

Watt demand

10～1kW or 0 ～2kW

Amp demand (R,S,T)
Active energy
Reactive energy

Measurement
3

30～5A （up to 20A)
1
1To t a l : 1 6 m e a s u r e m e n t s

Effect of temperature
Response time
Insulation resistanceWithstand voltage
Impulse test
Vibration & shock

Input voltage × VT ratio
Input active power × CT ratio
×VT ratio
Input reactive power × CT ratio ×
VT ratio
LEAD 0.0 ～100.0 ～LAG0.0 %45.00 ～65.0 0 Hz
Input watt demand × CT ratio ×VT ratio
Input current × CT ratio
0.000 ～ 999999 kWh
0.000 ～ 999999 kvarh

Auxiliary power supply
AC 80~264 V : 6VA
DC 80~143 V : 3.5W (32mA)
DC 19~ 31 V : 3.5W (150mA)

Environment and structure

Performance
Item
Tolerance

Indication
Input current × CT ratio

Specification
・・・ ±0.3%
CurrentVoltage・・・ ±0.3%
Active power・・・ ±0.5%
Reacti ve power ・・・ ±0.5%Power factor
・・・ ±0.03%
Frequency
・・・ ±0.5%
Watt demand・・・ ±1.0%
Amp demand・・・ ±1.0%
Active energy
・・・±1%+hour
Reactive energy ・・・±1%+hour±0.3% ／10℃
About 1 second
Over 100M Ω 500V DC
AC 2000V for 1 minute
6kV 1.2 ／50 μs
Vibration 10 ～55～10 Hz 0.15mm
Shock 490m/S 2 XYZ positive
And negative each 3 times.

Item
Operating temp
Storage temp
Humidity

Structure

WeightDisplay elementSpecification-10 ～ 55 ℃
-20 ～ 70 ℃
Under 8 5% RH
Case
polycarbonate
Cover
polycarbonate
Terminal cover polycarbonate
Terminal screw
brass（M4, M3）
About 520 gLCD

Output specification
Analog output
with limiter
Pulse output
Communication
outputRelay output

DC4 ～20mA 0 ～550 Ω
DC1 ～5 V 600 Ω～∽
Active energy or reactive energy
DC 125V 0.1A
RS -485 2400 ～9600bps(MODBUS)
Demand alarm. AC 250V 5A

Control input specification ( Remote control of main display)
The measurement item of a main display can be changed by impressing voltage from the exterior.
Please impress the voltage of AC 80~264V, or voltage of DC 80~143V.If it impress once, an item will move to next.
Consumption current is about 2mA.

Control input specification ( Alarm reset)
The alarm output can be cancelled by impressing voltage from the exterior. Please impress the voltage of AC 80~264V, or voltage of DC 80~143V.
If it impress once, the alarm output is cancelled and the operation replaces demand displays (MAX, MIN) with instantaneous measurements.
Consumption current is about 2 mA
2

TYPE NAME and SPEC No.
TPS － □□ －□ －□□Item
Circuit

No111221
22

Auxiliary
power supplyOption(Output)

3132333499
12900
1518252831325558Specification
1P 2W
1P2W
1P3W
1P3W

110V 5A
220V 5A
2×110V 5A
2×220V 5A

3P3W ／3P4W
110V or 110 ／√35A
3P3W ／3P4W
220V or 220 ／√35A
3P3W ／3P4W
380V or 380 ／√35A
3P3W ／3P4W
440V or 440 ／√35A
Others (note 1)
DC 19~31V
A C 80~264V and DC 80~143V
OthersNon
DC 1~5V (3ch)
DC 4~20mA (3ch)
DC 1~5V(2ch) + Wh or varh pulse
DC 4~20mA (2ch) + Wh or varh pulse
RS 485 (Modbus)
Demand Alarm + Reset
DC1~5V(1ch) + Demand Alarm + Reset
DC4~20mA(1ch) + Demand Alarm + Reset

Note 1: If you select spec No.99 , please consult with our company.
Example : 3P3W 230V 5A , 1P2W 110V 5ATPS

3.AUX power supply

4.Option－ □－ □□Internal parameters
TPS is carried out with the specified
The setting par ameters, which can be specified, are CT ratio, VT ratio, and the demand time limit.

parameters .

Example TPS -31-2-28

Case CoverLCD Display

45!