Cell 50 Ceiling
HunterDouglas® Cell Ceilings enablearchitects to design an open ceilingwith high-performance aluminium.
With a wide variety of cells andpatterns, these ceilings offer
maximum freedom in design.

Cell 50

2.6C

B22.6

150

B10.5

A1PANELS
Cell 50 panels are assembled fromaluminium U-profiles and create
perfect detailing of the connecting
U-profiles, which are designed toconceal uncoated edges.

410672b3bSUSPENSION
The 600 x 600 mm and600 x 1200 mm panels feature
an integrated system with mainand cross runners from the sameprofiles as the panels.
The panels are easily (de)mountedwith the sliding clips.
CONSTRUCTION DETAILSThe standard range of edge profiles
can be used.

52a3a

1 = Main runner 2400 mm
2a = Cross runner 1200 mm
2b = Cross runner 600 mm
3a = Cell tile 1200 x 600 mm
3b = Cell tile 600 x 600 mm
4 = Cell hanger

567

A = 1200 mm (max.)
B1 = Tile length (standard 1200)
B2 = Tile length (standard 600)
C = 300 mm (max.)

5Sliding clip

67567Adaptor bracket

Main runner splice

10MODULES AND HEIGHTS(Availability)

Tiles are made from 0.5 mm thickaluminium strip.

Module50 x 50
75 x 75
86 x 86

5.6 kg/m 2

3.8 kg/m 2

3.3 kg/m 2

2.8 kg/m 2

2.8 kg/m 2

1.9 kg/m 2

1.4 kg/m 2

15º
19º
24º
29º
33º
37º
50º

M200
M150
M120
M100
M86
M75
M50

Cell 50

50

MODULES, WEIGHTS AND
VIEWING ANGLES

M50

M75

M86

M100

M120

M150

M200

Height505050

MATERIAL REQUIREMENT PER M2
Edge profile type and quantity
is subject to individual projectrequirements.

HunterDouglas ® Ceilings - Cell

100 x 100
120 x 120150 x 150
200 x 200
Unit

Cell 50 tiles
Main Runners 2400
Cross Runners 1200
Cross Runners 600
Sliding Clips/Brackets
Splices
Cell Hangers

pcslmlmlm
pcs
pcs
pcs

Cell 50 Tile
1200 x 600
1.39
0.83
1.67
5.56
0.35
0.69

50
50
50
50
Cell 50 Tile
600 x 600
2.78
1.67
1.67
11.12
0.70
1.39

Perimeter
STANDARD PERIMETER OPTIONSCell 50

Half-blind runner (2400 mm)

L-edge profile (18.5 x 45 mm)

Cover profile(10 x 50 mm, 10 x 40 mm)

EDGE PROFILES

Wall L-profile alu(19.4 x 29.2)

Wall L-profile Fe/alu(18.5 x 45)

Wall W-profile Fe/alu(18.5 x 21 x 21 x 45)

CELL DIMENSIONSStandard dimensions are 600 x 600 mm and 600 x 1200 mm. Other sizes on request.

Material
SPECIFICATIONS- Base Material
Cell Ceiling systems are
manufactured from aluminium
alloy HD5050 or equal (accordingto EN 1396, and EN 13523
Series).
- Coating
The tough and durable 2-layer
polyester finish in a nominal
thickness of 20 microns is stoveenameled in a continuous coilcoating process to ensure uniform
coating thickness and absoluteadhesion.
- Colour range
The standard Hunter Douglasinterior colour range for Cell
Ceiling systems includes a wide
variety of colours and finishes. For
more information, see our colour
chart. Any other (RAL or NCS)
colour is available upon request.
HunterDouglas ® Ceilings - Cell- Tolerances
As a member of the Technical Association of Industrial Metal Ceiling
Manufacturers (TAIM), Hunter Douglas complies with tolerance criteria
as specified in the TAIM Quality standards for metal ceilings.
- Fire Behaviour
Hunter Douglas metal suspended ceilings are classified A2,s1,d0
according to EN 13501-1, and therefore will not contribute to fires.
Hunter Douglas Open Cell creates a ceiling through which large
amounts of air and or smoke can be extracted, a distinct advantage inescape routes where the clearest visibility is required.
- Plenum Accessibility
Hunter Douglas Cell Ceiling systems allow for easy (de)mounting of
the panels. The standard panels are easily lifted upwards and removed,
allowing full access to systems and installations in the plenum. The
minimum free space for comfortable (de)mounting is 130 mm. The
swing-down systems allow for (de)mounting the panels downward,
with the panels swinging and remaining suspended to allow for easyinteraction with the plenum. The sliding clips allow for (de)mounting of
the panels from below for cases where there is no handling space inthe plenum.

Belgium
Bulgaria
Croatia / Slovenia
Czech Republic
Denmark
FranceGermany
GreeceHungary

Wide Panel

Cell | Stretch metal

Italy
The Netherlands
NorwayPolandPortugal

LinearRomania

CurvedRussiaSerbiaSlovakia
Spain
SwedenScreenSwitzerland

Exterior

TurkeyUnited Kingdom
AfricaMiddle EastAsia

Tiles | XLnt panel

Australia
Latin America
North America

TM

Produced byHunter Douglas
Ceiling Center')68-*-)(&632>)

Hunter Douglas Architectural
Piekstraat 2P.O. Box 5072 - 3008 AB Rotterdam
The Netherlands
Tel. +31 (0)10 - 486 99 11
Fax +31 (0)10 - 484 79 10
www.hunterdouglasarchitectural.eu® Registered trademark - a HunterDouglas® product Pats. & Pats. Pend. - Technicaldata subject to change without notice. © Copyright Hunter Douglas 2018. Norights can be derived from copy, text pertaining to illustrations or samples. Subjectto changes in materials, parts, compositions, designs, versions, colours etc., even
without notice. MX074C00