QDP33

Manostar digital sensor
List ofproducts

WO81

WO71

FR51A

MS99

MS99S

QDP33

NEW
RoHS

30×30 type digital fine differential pressure sensor• Mounted with our originally developed electrostatic capacity type pressure sensor.
• Industry’s smallest size with a sensor, a display, and output function incorporated
in 30 mm square size.
• Close-contact mounting is possible.
• Employs easily visible large 12-segment LCD.
• Product compliant with UL standard and EU directive.
• An ultra-low pressure range product is newly added to the product lineup.
Product with 0 to 10 Pa range is optimum for room pressure measurement ofclean rooms compliant with the CDC guideline and negative pressure rooms.

MS61A-RA

QDP33

EMD8A

EMD7

EMT1

QDP33

EMTGP1

Installation example

EMT1H

EMT6

EMP5A

HWS15A<Main application fields>

Accessories
Application

Precautions
Maintenance• General factory management
equipment• Negative pressure for dust
collector/differential pressure of air
conditioner• Filter pressure loss management• Precision machine manufacturing
line• Building air conditioning control
equipment<Usage>• Detection of clogging of air filter• Room pressure measurement in aclean room
• Measurement of clogging of bug
filter• Measurement of dynamic pressure
at ventilation/exhaust device*(Refer to pages 114 to 117)

51

Vertical connection

Horizontal connection

EMRT1

Product code

QDP33

Ｎ

Pressure range code

1

D

200

(Example)

Range

Maximum value(for ± range, provide “±” as well)

Unit
Analog output
Comparison output◆When making an inquiry or placing an order, specify the above
product code.

D
E

Pa

1
4

4–20 mA

N
P

NPN transistor

kPa
1–5 V
PNP transistor

QDP33

Manostar digital sensor
QDP33

List ofproducts

Specifications
Model

QDP33
Analog output

Pressure unit

Pa, kPa

Pressuremeasurement
methodDifferential pressure method

Measured gas

Air and noncorrosive gas (liquid cannot be measured)

Sensor method

Electrostatic capacity typePressure-receiving
element

Diaphragm (silicone)

Mounting orientation

Mounting on vertical surface

Operating ambient
temperature

D10, D25, D ± 10, D ± 25: 0°C to 50°C (no freezing
allowed)
Other pressure range codes: 0°C to 60°C (no freezing
allowed)Operating ambient
humidity

35% to 85% RH or below (no condensation allowed)

Instrument bodywithstanding pressure

10 kPa (refer to page 118)

Withstanding pressureof pressure-receiving
element

10 kPa (refer to page 118)

Display

12-segment LCD (white/red), four digits
Main display
Sub display
12-segment LCD (orange), four digits
Accuracy	D10, D25, D ± 10, and D ± 25: ± 1.5% FS± 1 digit (at 23°C)
Other pressure range codes: ± 1.0% FS ±1 digit (at 23°C)
Temperature characteristics 	± 0.15% FS/°C (zero +span)

Zero adjustment
methodPush-type automatic zero return(The displayed value and analog output are adjusted tozero at the same time.)

Comparison output

Setting method: push-type digital setting
Output display Red LCD × 2
Output type
• QDP33N
Two systems of NPN open collector
Maximum load current: 100 mA or lower (per output)
Maximum load voltage: 30 V DC or lower
Output saturated voltage: 1 V DC or lower (at load
current of 100 mA)• QDP33P
Two systems of PNP open collector
Maximum load current: 100 mA or lower (per output)
Maximum load voltage: 30 V DC or lower
Output saturated voltage: 2 V DC or lower (at load
current of 100 mA)

Pressure range code
Ｄ 10
Ｄ 25
Ｄ 50
Ｄ 100
Ｄ 200
Ｄ 300
Ｄ 500
Ｄ 1000ＥＥ

12

Ｄ ＋− 10Ｄ ＋− 25
Ｄ ＋− 50
Ｄ ＋−100
Ｄ ＋−200
Ｄ ＋−300
Ｄ ＋−500
Ｄ ＋−1000
Ｅ ＋−1
Ｅ ＋−2

Rating pressure range

LCD display

0–10 Pa
0–25 Pa
0–50 Pa
0–100 Pa
0–200 Pa
0–300 Pa
0–500 Pa
0–1000 Pa

0.00–10.00
0.00–25.00
0.0–50.0
0.0–100.0
0–200
0–300
0–500
0–1000

0–1 kPa
0–2 kPa

0.00–1.00
0.00–2.00−10 to +10 Pa−25 to +25 Pa−50 to +50 Pa−100 to +100 Pa−200 to +200 Pa−300 to +300 Pa−500 to +500 Pa−1000 to +1000 Pa−10.00 to 10.00−25.0 to 25.0
−50.0 to 50.0−100 to 100−200 to 200−300 to 300−500 to 500−1000 to 1000

−1 to +1 kPa−2 to +2 kPa−1.00 to 1.00
−2.00 to 2.00

Accuracy 	Pressure range codes D10, D25, D ± 10, and D ±25: ± 1.5% FS (at 23°C)
Other pressure range codes: ± 1.0% FS (at 23°C)
Temperature characteristics ± 0.15% FS/°C (zero + span)
Output type
• QDP33□1
4 to 20 mA (biased pressure: 0 to FS, ±: at pressure of −50 to+50% FS)
Load resistance: 0 to 250 Ω• QDP33□4
1 to 5 V (biased pressure: 0 to FS, ±: at pressure of −50 to+50% FS)
Load resistance: 10 kΩ or higher

Power voltage

12 to 24 V DC ± 10% (ripple of 10% or below)

Maximum consumption
current

25 mA (at power voltage of 24 V)
Normal modeLow power consumption mode 20 mA (at power voltage of 24 V)*Excluding consumption currents in analog output and comparison
outputInsulation resistance

Between terminal and case 10 MΩ or higher (500 V DC megger)

Withstand voltage

Between terminal and case 500 V AC, 50/60 Hz, for one minute

Installation category
Operating altitude

Standard IEC 60664 level II(However, this product must be connected to the secondary sideof a safety insulation transformer, such as DC switching power.)
Altitude of 2000 m or below

Protection level

Standard: IEC 60529 Grade code: IP40

Degree ofcontamination

Standard: IEC 60664 Grade code: 2(If it is not possible to install this product at a dry clean location,
house it in a housing.)

Durable vibration
Durable impact

5 to 10 Hz, amplitude of 10 mm
10 to 50 Hz, acceleration of 39 m/s2 (two hours each for three
axial directions)
100 m/s2 (six times each for three axial directions)

Exterior material

PBT and polyamide

Pressure port

M5 internal thread
Metallic barb fitting (already installed on main body)
Applicable tube size: internal diameter of 4 mm
Indicating high-pressure side and low-pressure side with “H” and“L” marks, respectively, at pressure port.

Base polarity
Connector

RITS Connector 6P (TE Connectivity)

Mass

Approx. 30 g

Accessories

None (wiring-side connector and mounting parts are soldseparately)Comparison output

Analog output

WO81

WO71

FR51A

MS99

MS99S

MS61A-RA

QDP33

EMD8A

EMD7

EMT1

EMTGP1

EMT1H

EMT6

EMP5A
NPN transistor

4–20 mAoror

PNP transistor

1–5 V◆For use environment, refer to page 118.
Conforming standards
1. EU directive
This product is compliant with the EMC directive of EU.
EMC directive basic requirements Standard No............EN 61326‒1This product in combination with HWS15A-24/A (TDK-Lambda Corporation) is confirmed to be compliant with the EMC directive.
When using this product with other power unit, have the final system go through the EMC test.
2. UL standard
This product is certified as an UL standard recognition part. It is also certified with Canada Standard (C-UL).
However, use this product in accordance with the installation conditions shown in (3) below.
(1) Requirements standard No........................ UL 61010‒1(2) File No.......................................................... E220685(3) Installation condition .................................. As the DC power source to be connected to this product, use the NEC (National Electrical Code)Class 2 power source or LPS (Limited Power Source) power source.

EMRT1

HWS15A

Accessories
Application

Precautions
Maintenance52

QDP33

Manostar digital sensor
List ofproducts

WO81

QDP33
External dimension drawing

WO71

FR51A

MS99

32

30

(10)

î0
0RXQWLQJKROH

29

22.6

MS99S

5,76FRQQHFWRU3
(CN1)

9
7 2

30

MS61A-RA

φ4.7

6 5 4 3 2 1

H

L

MODE

QDP33

+LJKSUHVVXUHVLGH
SUHVVXUHSRUW

(1.5)

12

EMD8A

EMD7

EMT1

EMTGP1EMT1H

Operation panel

EMT6
Unit
Main display

EMP5A
Sub display

EMRT1

MODE

HWS15AUp keyAccessories
Application

Precautions
Maintenance

53

Comparison output
2 indication lamp

Comparison output
1 indication lamp

Down key

Mode key/RZSUHVVXUHVLGH
SUHVVXUHSRUW

QDP33

Manostar digital sensor
QDP33

List ofproducts

Terminal arrangement drawing

WO81654321

H

WO71

Pin 1: Power + (12 to 24 V DC)
Pin 2: Power − (0 V)
Pin 3: Analog output +Pin 4: Comparison output 1
Pin 5: Comparison output 2
Pin 6: NC (unused terminal)

L

FR51A

MS99

MS99S

MS61A-RA

Connection example
Comparison output: NPN transistor type
QDP33N type

DC power＋ source

CN1 (RITS connector 6P)

12‒24 VPower
circuit0V

Analog output circuit

ANALOGNPN transistor

OUTPUT 1

１
２
３
４
５
６

１
２
３
４
５
６

DC power
source ＋External device

12‒24 V

30V Max.

Common－－０Ｖ
Input ＋

EMD8A
Load

Input －

100mA Max.

QDP33

EMD7

Input

Comparison output 1 circuit

EMT1

NPN transistor

100mA Max.

OUTPUT 2

Input

Comparison output 2 circuit

EMTGP1EX.INPUT

External input circuit

EMT1H
Comparison output: PNP transistor type
External device

QDP33P type12‒24 VPower
circuit
Analog output circuit

0V
ANALOG

External input circuit

12‒24 V

Input ＋－

Input －

EMP5A
Load

Input

EMRT1

Input

HWS15AOUTPUT 1
100mA Max.

PNP transistor
Comparison output 2 circuit

１
２
３
４
５
６

100mA Max.

PNP transistor
Comparison output 1 circuit

１
２
３
４
５
６

EMT6

＋ DC power source

CN1 (RITS connector 6P)

OUTPUT 2
EX.INPUT

CommonAccessories
Application

Precautions
Maintenance54

QDP33

Manostar digital sensor
List ofproducts

WO81

QDP33
Panel mounting diagram and panel cutting dimensions
Panel cutting 31 mm

WO71

Rear face panel adapter

FR51A

MS99

MS99S
Panel

MS61A-RA
QDP33

QDP33

Front face panel adapter 31 mm square

EMD8A

EMD7
Front face panel adapter

EMT1

7.2

24.8

Rear face panel adapter

EMTGP150

33.465432 1

34.5

EMT1H

33.4

34.5

H

MODE

L

EMT6
(9.1)

EMRT1

Panel cutting dimensions

For mounting one piece
0.0

31-0.4

When n pieces are installed horizontally

Precautions
Maintenance

55

0.0

55 or more

Application

31-0.40.0

31-0.4

HWS15A

Accessories

When n pieces are installed vertically

31 × n pieces + 3.5 × (n pieces − 1)

55 or more
31 × n pieces + 3.5 × (n pieces − 1)

EMP5A

Mounting plate thickness 1 to 6

0.0

31-0.4

QDP33

Manostar digital sensor
QDP33

List ofproducts

Panel mounting diagram and panel cutting dimensions

WO81

Panel cutting 36 mm
Rear face panel adapter

WO71

FR51A

MS99

MS99S
Panel

MS61A-RA

QDP33

QDP33

EMD8A

Front face panel adapter 36 mm square

EMD7
Front face panel adapter

7.2

24.8

Rear face panel adapter

40

EMT1

33.4

EMTGP1

50

33.4

40

65432 1

H

MODE

L

EMT1H

EMT6
(9.1)

Mounting plate thickness 1 to 6

EMP5A

Panel cutting dimensions

EMRT1
For mounting one piece

When n pieces are installed horizontally+0.5

36 0.0

When n pieces are installed vertically

36 0.055 or more

36 × n pieces + 4 × (n pieces − 1)

55 or more

+0.5

36 0.0+0.5

36 × n pieces + 4 × (n pieces − 1)

HWS15A

Accessories
Application

Precautions
Maintenance+0.5

36 0.056

QDP33

Manostar digital sensor
List ofproducts

WO81

QDP33
Metallic bracket set for mounting use (separately sold) Installation diagram
Installation direction pattern 1

WO71

21.5

4×

4.2

9.5

FR51A

32

MS99

14.5

(R)

MS99S
Supplied M3 screws
are used.

MS61A-RA

QDP33

(1.5)

15

MODE

EMD7

30

(1.2)

EMD8A

45

30

49

65432 1

Metallic mounting
bracketEMT1

EMTGP1
Installation direction pattern 2
EMT1H
21.5

9.5

4×
(R)

18.7

4.2

EMP5A

14.5

EMT6

EMRT1

HWS15A

Accessories
49654321

15
30

(1.5)

(1.2)

MODE

Maintenance

57

45

Precautions

30

Application

QDP33

Manostar digital sensor
QDP33

List ofproducts

Mode changeover (1)WO81
Sub setting mode (SET2-MODE)

Before turning on of power supply

WO71[Turn on power supply]

MODE

FR51A

Output 1 function Sets the operation mode of output 1 function.

<For 100 Pa range>

Hysteresis mode
Window mode

Minimum scale indication(one second)

MS99

MODE

Output 1 mode Sets the output mode of output 1.

Maximum scale indication(one second)

Maximum value indication

Output 1 on-delay time

Protection setting

Holding down
for two seconds
Clearing ofretained value

Sets the off-delay time of output 1 function.

～

Cancellation ofprotection

MODE

Blinks once＋

Holding down for
two seconds

Pressure indication mode＋

Holding down for
two seconds

Upper limit over range indication
Biased pressure range: +110% FS or higher+− range: +60% FS or higher

Normal display

Lower limit over range indication
Biased pressure range: −10% FS or lower+− range: − 60% FS or lower

Display during sleep

MODE

MODE

Sets the on-delay time of output 1 power supply.

～
MODE

When no key has been pressed for 15 seconds,
the mode automatically returns to the pressure
indication mode.
(Excluding sub setting mode and detailed
setting mode)

Measurement pressure indication

MS61A-RA

QDP33

0 to 600 seconds(in units of 1 second)

Output 1 power supply on-delay time

Holding down
for two seconds
Clearing of retained value
MODE

0 to 600 seconds(in units of 1 second)

MODE

Output 1 off-delay time

Alternates between
Set and Cancel

Inversion of main
display colorEverysecondSets the on-delay time of output 1 function.

～

Blinks once

Minimum value indication

MS99S

MODE

Setting value
protection

Zero adjustment

Everysecond

OFF
N.C.
N.O.

EMD8A

0 to 20 minutes(in units of 1 minute)

EMD7

MODE

Output 2 function Sets the operation mode of output 2 function.

MODE

Hysteresis mode
Window mode

Holding down
for two seconds

MODE Holding down

for two seconds

EMT1

MODE

Output 2 mode Sets the output mode of output 2.
OFF
N.C.
N.O.

EMTGP1

MODE

Output 2 on-delay time

Sets the on-delay time of output 2 function.

～

0 to 600 seconds(in units of 1 second)

Holding down for two seconds

EMT1H

MODE

Main setting mode
（ＳＥＴ１－ＭＯＤＥ）

Output 2 off-delay time～

Output 1 function
In window mode

EMT6

0 to 600 seconds(in units of 1 second)

EMP5A

MODE

MODE

Output 1 function
In hysteresis mode

Sets the off-delay time of output 2 function.

Output 2 power supply on-delay time

Sets the output 2 power supply on-delay time.

～

0 to 20 minutes(in units of 1 minute)

EMRT1

MODE
MODE

MODE

Error indication (when an error occurs: when two errors haveoccurred at the same time)
MODE

MODE

Measurement
Measurement
Error code indication
Error code indicationpressure indicationpressure indication

Accessories

Output 2 function
In window mode

Output 2 function
In hysteresis mode

MODE

MODE

After every indication of pressure, the error codes are displayed in order at intervals of one second.

Application

Sub display when the key is held down

Precautions

Explanation of marks
MODE

MODE

HWS15A

MODE

Maintenance

Press the <<Mode>> key.
Press the <<Up>> key.

At the pressure setting points (P1, P2, Hi, and Lo), pressure values are set.
Setting range: Within the pressure range Units: Pa, kPa
P1: Pressure setting point in hysteresis mode
Hi: Upper limit pressure setting point in window modeP2: Hysteresis pressure setting point in hysteresis mode
Lo: Lower limit pressure setting point in window mode＋

Press the <<Down>> key.
Press the indicated keys simultaneously.
Blinking58

QDP33

Manostar digital sensor
List ofproducts

WO81

QDP33
Mode changeover (2)Detailed setting mode (SET3-MODE)

WO71

MODE

FR51A

Sub display
indication setting

Number setting

Set a two-digit number.
MODE

MODE

MODE

MODE

MODE

MODE

MS99

MS99S

Pressure
indication mode

MODE

MODE

Holding down
for fourseconds

MODE

Holding down
for twoseconds

MODE

MODE

Pressing <<Up>> key and <<Down>> key changes the character, and pressing the <<Mode>> key switches the digit. For thecharacters that can be set, refer to the list of setting characters below.
Pressing the <<Mode>> key when the cursor is at the rightmost digit confirms the entered characters, and proceeds to the next mode.

MS61A-RA

List of characters that can be set

QDP33

EMD8A
Indication filter

Sets the average move time of the indication filter.

0.2 seconds
1.0 seconds
2.0 seconds
5.0 seconds
10.0 seconds

Sets the average move time of the output filter.

0.2 seconds
1.0 seconds
2.0 seconds
5.0 seconds
10.0 seconds

EMD7
MODE

Output filter

EMT1
MODE

EMTGP1

Indication low cut Sets the indication low cut value.
0% to 5% FS(in units of 1% FS)
MODE

EMT1H

Output low cut

Sets the output low cut value.
0% to 5% FS(in units of 1% FS)

EMT6

MODE

Main display color

EMP5A

Sets the display color during indication of measured pressure.
White (measured pressure in white, others in red)Red (measured pressure in red, others in white)

MODE

Low power consumption Sets the power consumption mode.

Low consumption OFF
Low consumption ON
Sleeps in three minutes.

EMRT1
MODE

HWS15A

Measurement indication
Sets the symbol inversion for measurement indication value.
symbol inversion
OFF
ON
MODE

Accessories
Application

Precautions

Analog output inversion

Sets inversion of analog output.
OFF
ON

MODE

Test modeEnters the test mode, and sets a simulated pressure value. (Unit: Pa or kPa)
MODE

Maintenance
MODE

Setting clear～
Blinking

Blinking
MODE

Returns the setting value to the initial setting.
NO (does not clear the setting value)
YES (clears the setting value)

MODE

59

Pressure setting range:
biased pressure range −10 to 110% FS+− range −60% to +60% FS

QDP33

Manostar digital sensor
QDP33

List ofproducts

Comparison function operation diagrams

WO81

Comparison function
Hysteresis mode: upper limit setting (P1 > P2)

Comparison function
Hysteresis mode: lower limit setting (P1 < P2)$ODUP$ODUPDFWLYDWLRQ FDQFHOODWLRQ

3UHVVXUH

33
8SSHUOLPLWK\VWHUHVLV

Ｐ１

WO71

$ODUP$ODUPDFWLYDWLRQ FDQFHOODWLRQ

3UHVVXUH

FR51A

Ｐ２

MS99

Ｐ２

33Ｐ１

3UHVVXUHFRQGLWLRQ

1RUPDO

7LPH
1RUPDO$EQRUPDO&RPSDULVRQRXWSXWFRQGLWLRQＯＦＦ

2XWSXW
PRGH

Ｎ.Ｃ.

1RUPDO$EQRUPDO

7LPH
1RUPDO&RPSDULVRQRXWSXWFRQGLWLRQ

1RUPDOO\RSHQ 2))&ORVH 21
2SHQ 2))Ｎ.Ｏ.

3UHVVXUHFRQGLWLRQ/RZHUOLPLWK\VWHUHVLV

2SHQ 2))

&ORVH 21&ORVH 21

2SHQ 2))2XWSXW
PRGH

ＯＦＦ
Ｎ.Ｃ.

Ｎ.Ｏ.

MS61A-RA

1RUPDOO\RSHQ 2))&ORVH 21

2SHQ 2))

&ORVH 21

2SHQ 2))

&ORVH 21

2SHQ 2))

Operation explanation:	Detects an abnormal pressure rise, and activates comparison
output.
When the output mode is set to N.C., the output will open (OFF)when the applied pressure exceeds the setting value P1, and willclose (ON) when the pressure falls below P2.
Power on-delay timer:	During the operation of the timer, the comparison output will
forcefully open (OFF).

Operation explanation:	Detects an abnormal pressure drop, and activates comparison
output.
When the output mode is set to N.C., the output will open (OFF)when the applied pressure falls below the setting value P1, andwill close (ON) when the pressure exceeds P2.
Power on-delay timer:	During the operation of the timer, the comparison output will
forcefully open (OFF).

Comparison function
Window mode: internal area (Hi > Lo)

Comparison function
Window mode: external area (Hi < Lo)$ODUP$ODUP$ODUP$ODUP

3UHVVXUH FDQFHOODWLRQ DFWLYDWLRQ FDQFHOODWLRQ DFWLYDWLRQHi

3UHVVXUH+\VWHUHVLV

％)6

Lo

QDP33

EMD8A

EMD7

$ODUP$ODUP$ODUP$ODUPDFWLYDWLRQ FDQFHOODWLRQ DFWLYDWLRQ FDQFHOODWLRQ+\VWHUHVLV

MS99S

EMT1

％)6

EMTGP1

3UHVVXUHFRQGLWLRQ

Hi

％)6

Lo

％)6

EMT1H

$EQRUPDO

1RUPDO$EQRUPDO

7LPH$EQRUPDO

1RUPDO&RPSDULVRQRXWSXWFRQGLWLRQ
2XWSXW
PRGH+\VWHUHVLV+\VWHUHVLV

ＯＦＦ

Ｎ.Ｃ. 2SHQ 2))
Ｎ.Ｏ. &ORVH 21$EQRUPDO

7LPH
1RUPDO

1RUPDO$EQRUPDO&ORVH 21
2SHQ 2))

2SHQ 2))

&ORVH 21&ORVH 21

2SHQ 2))EMT6

&RPSDULVRQRXWSXWFRQGLWLRQ

1RUPDOO\RSHQ 2))&ORVH 21
2SHQ 2))

3UHVVXUHFRQGLWLRQ 1RUPDO

2SHQ 2))

&ORVH 21

2SHQ 2))

&ORVH 21

2SHQ 2))

&ORVH 21

Operation explanation:	The comparison operation is performed in the range of the set
pressure area from Lo to Hi (window).
When the output mode is set to N.C., the output will close (ON)when the applied pressure is within the range (window) and will
open (OFF) when the pressure is out of the range.
Power on-delay timer:	During the operation of the timer, the comparison output will
forcefully open (OFF).

2XWSXW
PRGH

ＯＦＦ

Ｎ.Ｃ. &ORVH 21

Ｎ.Ｏ. 2SHQ 2))

1RUPDOO\RSHQ 2))
2SHQ 2))
&ORVH 21

Operation explanation:	The comparison operation is performed in the range outside theset pressure area from Hi to Lo.
When the output mode is set to N.C., the output will close (ON)when the applied pressure is out of the range, and will open (OFF)when the pressure is within the range.
Power on-delay timer:	During the operation of the timer, the comparison output will
forcefully open (OFF).

EMP5A

EMRT1

HWS15A

Comparison output delay (On, Off, Power supply on)

Accessories

3RZHUVXSSO\21

5HVXOWRILQWHUQDOFRPSDULVRQApplication
2SHQ 2))

&ORVH 21
3RZHU21GHOD\WLPH
WRPLQXWHV

21GHOD\WLPH2))GHOD\WLPH
WRVHFRQGV

2SHQ 2))

&ORVH 21

Operation explanation:	Regardless of the output mode setting (N.C., N.O.), the closeand open (ON and OFF) timings of output transistor are delayedby the set delay time.
Power on-delay timer:	During the operation of the timer, the comparison output will
forcefully open (OFF).

Precautions
Maintenance

21GHOD\WLPH
WRVHFRQGVWRVHFRQGV&RPSDULVRQRXWSXW&ORVH 21

2SHQ 2))

&ORVH 21

60

QDP33

Manostar digital sensor
List ofproducts

WO81

WO71

FR51A

QDP33
QDP33 accessories

RoHS

RITS 5P cable w/connector
This is a cable with connector used for connection with
QDP33.
In the sheath cable and other constituting parts of thisproduct, vinyl chloride is not intentionally used.
RITS plugs and connectors are products of TE Connectivity.
Item number

Cover color

Core wire
insulation sheath
color

CAB-RITS5-15

Yellow

MS99S！
MS61A-RA

QDP33

EMT1

This product is not UL-certified.

EMT1H

EMT6

EMP5A

EMRT1

HWS15A

Accessories
Application

Precautions
Maintenance

61

6KHDWKFDEOH EODFNĳILYHFRUHV（15）1500 +500（50）Core wire sheath outer diameter: 1.0 mm
Standard: AWG#24

RITS plug/connector 5P (TE Connectivity)
This is a wiring side plug/connector used on QDP33.

Cover: yellow

Applicable wiring
Item number

Color

Nominal crosssection area

Finish outer
diameter

1473562-5

Yellow

0.1–0.5 mm2

1.0–1.15 mm！
CautionEMTGP1①②③④⑤

Caution

EMD8A

EMD7

Terminal
number

Brown
Blue
Pink
Black
White

MS99

5,76SOXJFRQQHFWRU3

When crimping of connector is performed, use the dedicated tool (item number: 1729940-1 from TE Connectivity).
For other RITS connectors and details, contact TE Connectivity.

*Cable is not supplied.

QDP33

Manostar digital sensor
QDP33

List ofproducts

QDP33 accessories

RoHS

VT base (Nihon Pisco Co., Ltd.)PT base (Nihon Pisco Co., Ltd.)PR base (Nihon Pisco Co., Ltd.)

WO81

WO71

FR51A

MS99
Item number

KGAVT-M5

Material

Brass

Item number

KGAPT-M5

Material

Brass, PBT, NBR

Item number

KGAPR-M5

Material

Brass, PBT, NBR

It is possible to connect a vinyl pipe orrubber pipe with an inner diameter of 4mm. This is already installed at the timeof purchase of the instrument.

The tube mounting part is a push-in joint.
For piping, use the separately sold tube ora tube compliant with JIS B 8381-1. (Outer
diameter of connectable tube: 6 mm)
For mounting, a hex wrench with a width
across flats of 2.5 mm is necessary.

The tube mounting part is a rotary elbow
push-in joint. The piping is same as thatfor PT base.
For mounting, a hex wrench with a width
across flats of 3 mm is necessary.

Front face panel adapter 31 mm square

Front face panel adapter 36 mm square

Rear face panel adapter

MS99S

MS61A-RA

QDP33

EMD8A

EMD7

Item number

ADP33-31

Material

Polypropylene

For panel cutting 31×31 mm
When installing the instrument body in apanel, this product is used in combination
with the rear face panel adapter.

Metallic bracket set for mounting use

Item number

ADP33-36

Material

Polypropylene

For panel cutting 36×36 mm
When installing the instrument body in apanel, this product is used in combination
with the rear face panel adapter.

Item number

ADP33-B

Material

Polypropylene

When installing the instrument body in apanel, this product is used in combination
with the front face panel adapter.

Color cap for PT base/PR base (Nihon Pisco Co., Ltd.)
High-pressure side

EMT1

Low-pressure side

EMTGP1

EMT1H

EMT6

EMP5A

EMRT1
Item number

BRKT-QDP

Material

Steel

This is used when installing the instrument
body on a floor surface or ceiling surface.

Item number

KGACAPM6-H

Material

Polyacetal

Item number

KGACAPM6-L

Material

PolyacetalThis helps identify the high-pressure side and low-pressure side and prevents the tube
from being disconnected because of an erroneous operation.

HWS15A

Accessories
Application

Precautions
Maintenance62

Warranty■Warranty period
The warranty period for our product is one (1) year from delivery to the location specified by the orderer who makes a direct transaction
with us.

■Scope of warranty
If any failure or defect attributable to us becomes clear during the above warranty period, we will repair the product or supply asubstitute product free of charge. However, even during the warranty period, we will exclude the product from the scope of the warranty
if the failure or defect corresponds to any of the following:(1) The failure or defect was caused by an unreasonable condition, environment, handling, or usage not mentioned in the
instruction manual, specifications, and our product catalog.
(2) The failure or defect was caused by a factor other than our product.
(3) The failure or defect was caused by a modification or repair conducted by a party other than us.
(4) The failure or defect was caused by an event that could not be foreseen at the scientific and technical levels at the time of
product shipment from us.
(5) The failure or defect was caused by an external factor not attributable to us, such as acts of God and disasters.
Please note that the warranty mentioned here means the warranty for our individual product, and damage provoked by a failure or
defect of the product is excluded from the scope of the warranty.
*This warranty is valid only in Japan.

Application and usage
Our products are designed and manufactured as general-purpose instruments for general industries.
Therefore, our products are not intended for the following uses, and our products used in such a manner are outside the scope of
application.
(1) Equipment that is anticipated to greatly affect lives and properties, such as nuclear power generation, aviation, railways, marine
vessels, vehicles, and medical devices(2) Utilities that include electricity, gas, and service water(3) Use in outdoor locations and under similar conditions or environments other than those stipulated in the instruction manual(4) Usage to which considerable safety consideration and attention equivalent to (1) and (2) above need to be given

Service■Scope of service
Because the product price does not include service expenses, such as the dispatch of engineers, we will separately charge for the
expenses in the following cases:(1) Instruction for installation and adjustment and a witnessed test run(2) Maintenance inspection, adjustments, and repairs(3) Technical guidance and technical education(4) Witnessed inspections of products at our factory<<Note>> The product specifications and information in this catalog are subject to change without prior notice for product improvement orother reasons.

●For order placement, contact

Generalagent

Manostar Shop Co., Ltd.

1-2-3 Nishishiriike-cho, Nagata-ku, Kobe City, Hyogo 653-0031
TEL. +81-78-621-7000 FAX. +81-78-621-7788

Manufacturer

Yamamoto Electric Works Co., Ltd.

1-2-3 Nishishiriike-cho, Nagata-ku, Kobe City, Hyogo 653-0031
TEL. +81-78-631-6000 FAX. +81-78-631-6020

SEPTEMBER 2021 YAMAMOTO ELECTRIC WORKS CO., LTD., JAPAN