for North America
SE3800H-US / SE5000H-US / SE6000H-US /SE7600H-US / SE11400H-US

12-25
YEAR
WARRANTY

INVERTERSEV Charging Single Phase
Inverter

Optimized installation with HD-Wave technology and EV Charger
Specifically designed to work with power optimizers

Extremely small and easy to install outdoors or indoors

Record-breaking efficiency

EV charger cable and holder ordered separately for
flexible cable length selection

Quick and easy inverter commissioning directly from asmartphone using the SolarEdge SetApp
Fixed voltage inverter for longer strings
Integrated arc fault protection and rapid shutdown for
NEC 2014 and 2017, per article 690.11 and 690.12
UL1741 SA certified, for CPUC Rule 21 grid compliancesolaredge.com

Integrated Level 2 EV charger with solar boost
mode charging (grid & PV)
Built-in module-level monitoring
Optional: Revenue grade data, ANSI C12.20 Class 0.5(0.5% accuracy)

EV Charging Single Phase Inverter
for North America

SE3800H-US / SE5000H-US / SE6000H-US / SE7600H-US / SE11400H-US
INVERTER SPECIFICATIONS:
SE3800H-US

SE5000H-US

SE6000H-US

SE7600H-US

SE11400H-US

Rated AC Power Output

3800500060007600

11400

Max. AC Power Output

3800

5000

6000

7600

11400

OUTPUT

AC Output Voltage Min.-Nom.-Max.

211 - 240 - 264

AC Frequency (Nominal)

59.3 - 60 - 60.5(1)Maximum Continuous Output Current

162125

GFDI Threshold

1

Utility Monitoring, Islanding Protection, Country
Configurable Thresholds

Yes

VA
VA
Vac
Hz

32

47.5

A
A

INPUT
Maximum DC Power

5900

7750

Transformer-less, Ungrounded

11800

17650

W

Yes

Maximum Input Voltage

480

Nominal DC Input Voltage
Maximum Input Current

9300

Vdc

380
10.5

13.5

400
16.5

Max. Input Short Circuit Current

45

Reverse-Polarity ProtectionYes

Vdc20

30.5

Adc
Adc

600k Sensitivity

Ground-Fault Isolation Detection
Maximum Inverter Efficiency

99.2%

CEC Weighted Efficiency

99%

Nighttime Power Consumption< 2.5W

ADDITIONAL FEATURES
Supported Communication Interfaces

RS485, Ethernet, ZigBee (optional), Cellular (optional)

Smart Energy Management

Export Limitation and Excess Solar Charging(2)Revenue Grade Data, ANSI C12.20
Inverter Commissioning

Optional(3)with the SetApp mobile application using built-in Wi-Fi access point for local connection

Rapid Shutdown - NEC 2014 and 2017 690.12

Automatic Rapid Shutdown upon AC Grid Disconnect

STANDARD COMPLIANCE
SafetyUL1741, UL1741 SA, UL1699B, CSA C22.2, Canadian AFCI according to T.I.L. M-07

Grid Connection Standards

IEEE1547, Rule 21, Rule 14 (HI)Emissions

FCC Part 15 Class B

INSTALLATION SPECIFICATIONS
1” maximum / 14-6 AWG

1” maximum /14-4 AWG

DC Input Conduit Size / # of Strings / AWG Range

1” maximum / 1-2 strings / 14-6 AWG

1” maximum /1-3 strings / 14-6
AWG

Dimensions with Connection Unit with Safety Switch(HxWxD)17.7 x 14.6 x 6.8 / 450 x 370 x 17421.3 x 14.6 x 7.3 /540 x 370 x 185

in / mm38.8 / 17.6lb / kg

AC Output Conduit Size / AWG Range

Weight with Connection Unit with Safety Switch
NoiseCooling
Operating Temperature Range
Protection Rating

22 / 1025.1 / 11.4

26.2 / 11.9

< 25<50dBA

Natural Convection-40 to +140 / -40 to +60(4)NEMA 4X (Inverter with Connection Unit with Safety Switch)(1) For other regional settings please contact SolarEdge support(2) Import/Export meter is required for Export Limitation and for controlled Excess Solar charging(3) Revenue grade meter P/N: SExxxxH-US000BNW4(4) Full power up to at least 50°C/122°F . For power de-rating information refer to: https://www.solaredge.com/sites/default/files/se-temperature-derating-note-na.pdf

˚F / ˚CEV Charging Single Phase Inverter
for North America

SE3800H-US / SE5000H-US / SE6000H-US / SE7600H-US / SE11400H-US
EV CHARGER AND EV CHARGER CABLE SPECIFICATIONS:OUTPUT — AC
AC Level 2Connection to the SolarEdge monitoring platform is required for first EV charging

Charging Level
Rated AC Power Output (grid & PV)

9600W

Nominal AC Output Voltage

240

Vac

Nominal AC Frequency

60

HzMaximum Continuous Output Current @240V (grid & PV)

40

Aac

Ground Fault Detection Threshold

5mA

ADDITIONAL FEATURESEV Charger Status LEDs, Fault Indicator
EV Charger Unplugging Detection
EV Charger Ground Connection Monitoring
EV Charger Configuration

Yes
Yes, current termination according to SAE J1772
Yes, continuous
Via the monitoring app; Ethernet / Cellular or ZigBee connection is required

STANDARD COMPLIANCE
SafetyUL2594, UL2231-1, UL2231-2, NEC Article 625 compliant

EV Charger

SAE J1772-2009

INSTALLATION SPECIFICATIONSEV Charger Connector

SAE J1772-2009

EV Charger Cable Length(5)

EV Charger Cable Weight
EV Charger Cable Operating Temperature Range
Protection Rating (connected to EV or with dust cap)

25 / 7.6ft / m

12.5 / 5.7lb / kg

-22 to +122 / -30 to +50

˚F / ˚C

NEMA 3R(5) EV charger cable ordered separately© SolarEdge Technologies Inc. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdgeTechnologies, Inc. All other trademarks mentioned herein are trademarks of their respective owners. Date: 07/2019/V01/ENG NAM. Subject to change without notice.