For North America
SE10KUS / SE17.3KUS
12-20
YEAR
WARRANTY

INVERTERS

Three Phase Inverters
for the 120/208V Grid

The best choice for SolarEdge enabled systems
Specifically designed to work with power
optimizers

Integrated arc fault protection and rapid shutdown
for NEC 2014 – 2023, per article 690.11 and 690.12

Quick and easy inverter commissioning directlyfrom a smartphone using SolarEdge SetApp

Built-in module-level monitoring with Ethernet,
wireless or cellular communication for full system
visibility

Fixed voltage inverter for superior efficiency andlonger strings
Built-in type 2 DC and AC Surge Protection, tobetter withstand lightning events
Small, lightest in its class, and easy to installoutdoors or indoors on provided bracket

solaredge.com

Integrated Safety Switch
UL 1741 SA and SB certified, for CPUC Rule 21 gridcomplianceThree Phase Inverters for the 120/208V Grid(1)For North America
SE10KUS / SE17.3KUS
Model Number

SE10KUS

Applicable to inverters with part number

SE17.3KUS
SEXXK-USX2IXXXXOUTPUT
Rated AC Power Output

10000

17300

W

Maximum Apparent AC Output Power10000

17300

VA

AC Output Line Connections

3W + PE, 4W + PE

AC Output Voltage Minimum-Nominal-Maximum(2) (L-N)

105 – 120 – 132.5

VacAC Output Voltage Minimum-Nominal-Maximum(2) (L-L)

183 – 208 – 229

Vac

AC Frequency Minimum-Nominal-Maximum(2)59.3 – 60 – 60.5

Continuous Output Current (per Phase)

27.8

GFDI Threshold
Utility Monitoring, Islanding Protection, Country Configurable
Set Points
THDHz
48.25

1

AacAYes≤3

Power Factor Range%+/- 0.85 to 1

INPUT
Maximum DC Power (Module STC)

17500

Transformer-less, UngroundedMaximum Input Voltage DC+ to DC-600

Operating Voltage Range
Maximum Input Current30275Vdc

370 – 600
27.855

Reverse-Polarity Protection

Yes

Ground-Fault Isolation Detection

Vdc
48.25

Maximum Input Short Circuit Current

CEC Weighted Efficiency

WYesAdc
Adc

167kΩ Sensitivity(3)97Night-time Power Consumption

97.5
<4%
W

ADDITIONAL FEATURES
Supported Communication Interfaces
Inverter Commissioning

2 x RS485, Ethernet, Cellular (optional)
With the SetApp mobile application using built-in Wi-Fi access point for local connection

Rapid Shutdown

NEC 2014 – 2023, built-in

RS485 Surge Protection Plug-in

Supplied with the inverter, built-in

AC, DC Surge Protection

Type II, field replaceable, built-in

DC Fuses (Single Pole)

25A, built-in

Smart Energy Management

Export Limitation

DC SAFETY SWITCHDC Disconnect

Integrated

STANDARD COMPLIANCE
SafetyUL 1741, UL 1741 SA, UL 1741 SB, UL 1699B, CSA C22.2, Canadian AFCI according to T.I.L. M-07

Grid Connection Standards
Emissions

IEEE 1547-2018, Rule 21, Rule 14 (HI)FCC Part 15 Class A

INSTALLATION SPECIFICATIONSAC Output Conduit size /AWG range¾” or 1” / 6 - 10 AWG

DC Input Conduit size / AWG range¾” or 1” / 6 - 12 AWG

Number of DC inputs pairs
Dimensions with Safety Switch (H x W x D)
Weight with Safety Switch
Cooling
Noise
Operating Temperature Range
Protection Rating
Mounting

431.8 x 12.5 x 11.8 / 808 x 317 x 300in / mm

78.2 / 35.5

lb / kg

Fans (user replaceable)< 62dBA-40 to +140 / -40 to +60(4)˚F / ˚C

NEMA 3R
Bracket provided(1) For 277/480V inverters refer to the Three Phase Inverters for the 277/480V Grid for North America datasheet.
(2) For other regional settings please contact SolarEdge support.
(3) Where permitted by local regulations.
(4) For power derating information refer to the Temperature Derating technical note for North America.

© SolarEdge Technologies, Ltd. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdge Technologies, Inc.
All other trademarks mentioned herein are trademarks of their respective owners. Date: May 16, 2024 DS-000069-NAM. Subject to change without notice.