Regency Horizon™ HZ54E
Gas Fireplace

Owners &Installation Manual
MODELS: HZ54E-NG Natural Gas
HZ54E-LP Propane

www.regency-fire.com
WARNING:
If the information in these instructions are not followed exactly,
a fire or explosion may result causing property damage,personal injury or loss of life.

FOR YOUR SAFETY
What to do if you smell gas: Do not try to light any appliance Do not touch any electrical switch:
do not use any phone in yourFOR YOUR SAFETY
building.
Do not store or use gasoline or other flammable vapors and  Immediately call your gas supplierliquids in the vicinity of this or any other appliance.
from a neighbour's phone. Follow
the gas supplier's instructions.
Installation and service must be performed by a qualified
 If you cannot reach your gas
installer, service agency or the gas supplier.
supplier, call the fire department.
Tested by:

Installer: Please complete the details on the back coverand leave this manual with the homeowner.
Homeowner: Please keep these instructions for future reference.
918-883b

FPI FIREPLACE PRODUCTS INTERNATIONAL LTD. 6988 Venture St., Delta, BC Canada, V4G 1H4

04/12/11

To the New Owner:

Congratulations!
You are the owner of a state-of-the-art Gas Fireplace by REGENCY®. The HZ54E has been
designed to provide you with all the warmth and charm of a wood fireplace at the flick of a switch.
The model HZ54E has been approved by Warnock Hersey/Intertek for both safety and efficiency.
As it also bears our own mark, it promises to provide you with economy, comfort and security formany trouble free years to follow. Please take a moment now to acquaint yourself with these
instructions and the many features of your Regency® Fireplace.

2

Regency Horizon HZ54E Gas Fireplace

MANUFACTURED MOBILE HOME REQUIREMENTS
INFORMATION FOR MOBILE/MANUFACTURED HOMES AFTER FIRST SALE
This Regency® product has been tested and listed by Warnock Hersey/Intertek as a Direct Vent Wall Furnace to the following
standards: VENTED GAS FIREPLACE HEATERS ANSI Z21.88-2009 / CSA 2.33-2009 and GAS-FIRED APPLIANCES FOR
USE AT HIGH ALTITUDES CAN / CGA 2.17-M91.
This appliance may only be installed in an aftermarket permanently located, manufactured (U.S.A only) or mobile home,where not prohibited by local codes.
This Direct Vent System Appliance must be installed in accordance with the manufacturer's installation instructions and the
Manufactured Home Construction and Safety Standard, Title 24 CFR, Part 3280, or the current Standard of Fire Safety Criteriafor Manufactured Home Installations, Sites, and Communities ANSI/NFPA 501A, and with CAN/CSA Z240-MH Mobile Home
Standard in Canada.
This appliance installation must comply with the manufacturer's installation instructions and local codes, if any. In the absenceof local codes follow the current National Fuel Gas Code, ANSI Z223.1 and the current National Electrical Code ANSI/NFPA
70 in the U.S.A., and the current CAN/CGA B149 Gas Installation Code and the current Canadian Electrical Code CSA C22.1
in Canada.
This appliance comes equipped with a dedicated #8 Ground Lug for attachment of the ground wire to the steel chassis asapplicable to local codes.
The appliance, when installed, must be electrically grounded in accordance with local codes or, in the absence of local codes,
with the National Electrical Code, ANSI/NFPA 70, or the Canadian Electrical Code, CSA C22.1.
This appliance can only be used with the type of gas indicated on the rating plate.
This appliance is not convertible for use with other gases.
Ensure that structural members are not cut or weakened during installation.
This appliance may be installed as an OEM installation in a manufactured home (USA only) or mobile home and must be
installed in accordance with the manufacturer's instruction and the Manufactured Home Construction and Safety Standard,
Title 24 CFR, Part 3280, in the Untied States, or the Standard for Installation in Mobile Homes, CAN/CSA Z240 MH, in
Canada.

Regency Horizon HZ54E Gas Fireplace

3

TABLE OF CONTENTSSAFETY LABEL
Copy of Safety Decal .....................................................5

REQUIREMENTS
MA Code - CO Detector.................................................6

DIMENSIONS
Unit Dimensions ............................................................7
Faceplate & Door frame overlay Dimensions ................7

INSTALLATION
Important Message ......................................................8
Before You Start ............................................................8
General Safety Information............................................8
Installation Checklist ......................................................9
Locating Your Gas Fireplace .........................................9
Heatwave kit ..................................................................9
Heatrelease kit...............................................................9
Clearances ..................................................................10
Non-Combustible Requirements .................................10
Top non-combustible facing board............................... 11
Mantel Clearances.......................................................12
Mantel Leg Clearances................................................12
Framing & Finishing.....................................................13
Unit Assembly Prior To Installation ..............................15
Standoff Assembly ...............................................15
Nailing Strips........................................................15
Venting Introduction .....................................................15
Vent Restrictor Position ...............................................16
Exterior Vent Termination Requirements .....................17
Venting Arrangements ................................................18
Horizontal Termination (Flex) ...............................18
Rigid Pipe Venting Systems ........................................19
Basic Horizontal & Vertical Terminations .............195” x 8” Rigid Pipe Cross Reference Chart ...................20
Venting Arrangements ................................................22
Allowable Horizontal Terminations for HZ54E-ng 22
Venting Arrangements ................................................22
Allowable Horizontal Terminations for HZ54E-lp .22
Venting Arrangements ................................................25
Allowable Vertical Terminations for HZ54E-ng.....25
Venting Arrangements ................................................26
Allowable Vertical Terminations for HZ54E-lp ......26
Unit Installation with Horizontal Termination ................27
Unit Installation with Vertical Termination ....................28
Unit Installation ............................................................29
Horizontal Termination .........................................29
with Flex Vent System .........................................29
High Elevation .............................................................30
Gas Line Installation ....................................................30
4

Pilot Adjustment ...........................................................30
Gas Pipe Pressure Testing ..........................................30
886 S.I.T. Valve ...........................................................30
Valve cover removal ....................................................31
Aeration Adjustment ....................................................32
Wiring Diagram ............................................................32
Proflame system GTMF with optional fan....................33
Optional fan Wiring Diagram ......................................34
Optional Wall Thermostat ...........................................35
Optional Remote Control .............................................35
Wall Switch ..................................................................35
Battery & on | off switch installation ............................37
GT remote installation .................................................38
GTM remote installation ..............................................39
GTMF remote installation ............................................41
Optional Reflective Panel Installation ..........................43
Glass Crystals or optional ceramic stones ..................44
Installation On Burner ..................................................44
Glass Crystals or optional pebbles ..............................45
Installation On firebox base .........................................45
Optional Log set Installation ........................................46
Faceplate & Door frame overlay Installation................49
Optional fan installation ...............................................51

OPERATING INSTRUCTIONS
Operating Instructions .................................................54
First Fire ......................................................................54
Lighting Procedure ......................................................54
Shutdown Procedure ...................................................54
Normal Operating Sounds of Gas Appliances .............54
Copy of Lighting Plate Instructions ..............................55

MAINTENANCE
Maintenance Instructions.............................................56
General Vent Maintenance ..........................................56
Glass Gasket ...............................................................56
Glass Door...................................................................56
Glass Replacement .............................................56
Glass Door Removal ...................................................57
Valve Tray Replacement..............................................58
HZ54E-NG unit ............................................................59
HZ54E-LP unit .............................................................60

PARTS LIST
Main Assembly ............................................................61
Accessories .................................................................62

WARRANTY
The Warranty: Limited Lifetime ...................................63

Regency Horizon HZ54E Gas Fireplace

SAFETY LABELThis is a copy of the label that accompanies
each HZ54E-NG and HZ54E-LP Direct Vent
Gas Fireplace. We have printed a copy of thecontents here for your review.
NOTE: Regency® units are constantly being
improved. Check the label on the unit and if
there is a difference, the label on the unit is thecorrect one.

COPY OF SAFETY DECAL

Duplicate S/N

363

DO NOT REMOVE THIS LABEL / NE PAS ENLEVER CETTE ÉTIQUETTE
Listed: VENTED GAS FIREPLACE HEATER / FOYER AU GAZ À ÉVACUATION
Certified for/Certifiée pour: CANADA and U.S.A.
Serial No./ No de serie
Tested to: CAN/CGA-2.17-M91,ANSI Z21.88a-2007/CSA 2.33a-2007
4001172363

MAY BE INSTALLED IN MANUFACTURED (MOBILE) HOMES AFTER FIRST SALE.

NATURAL GAS: Model HZ54E-NG
Min. Supply Pressure
Low Setting Man. Pressure
Max. Manifold Pressure
Orifice Size
Minimum Input
Maximum Input
Altitude

5“ WC(1.25 kpa)
1.6"WC(0.40 kpa)
3.5"WC(0.87 kpa)
#30DMS
29,000Btu/h (8.50 kW)
41,500 Btu/h (12.16 kW)
0-4500 ft/pi (0-1372 m)

PROPANE GAS: Model HZ54E-LP
Min. Supply Pressure
Low Setting Man. Pressure
Max. Manifold Pressure
Orifice Size
Minimum Input
Maximum Input
Altitude

12“WC(2.98 kpa)
6.4"WC(1.59 kpa)
10"WC
(2.49 kpa)
#49 DMS
30,000Btu/ (8.79 kW)
37,000Btu/h (10.84 kW)
0-4500 ft/pi (0-1372 m)

APPAREIL FONCTIONNANT AU NATURAL GASCONCU POUR CET POELE: Modéle HZ54E-NG
Pression d'allimentation minimum
Pression à la tubulure d'échappement élevée
Pression à la tubulure d'échappement basse
Grandeur de l'injecteur
Débit Calorifique minimum selon
Débit Calorifique maximum selon
l'altitude
ÉQUIPÉ A L'USINE POUR GAZ PROPANE
CONCU POUR CET POELE: Modéle HZ54E-LP

Pression d'allimentation minimum
Pression à la tubulure d'échappement élevée
Pression à la tubulure d'échappement basse
Grandeur de l'injecteur
Débit Calorifique minimum selon
Débit Calorifique maximum selon
l'altitude

Minimum Clearances to Combustibles /Degagement Minimum De Materiaux Combustibles

B
D

F
A

C

E

DOOR SEAL: Pleasecheck that the door isproperly sealed

Side Walls
A4” (102mm)
CeilingB40-7/8” (1038mm)
Min. Mantel HeightC20" (508mm)
Max. Mantel Depth
D13” (330mm)
Alcove WidthE83" (2108mm)
Alcove DepthF36" (914mm)(See Instruction Manual for
detailed instructions)

FPI Fireplace Products International Ltd. Delta, BC, CanadaThis appliance must be installed in accordance with local codes, if any; if none, follow the National Fuel Gas Code, ANSI Z223.1, or Natural Gas and Propane Installation Code, CSA B149.1.
This appliance must be installed in accordance with the Standard CAN/CSA Z240 MH, Mobile Housing, in Canada, or with the Manufactured Home Construction and Safety Standard, Title 24 CFR, Part 3280, in
the United States, or when such a standard is not applicable, ANSI/NCSBCS A225.1/NFPA 501A, Manufactured Home Installations Standard or ANSI A119.2 ou NFPA 501C Standard for Recreational Vehicles
This appliance is only for use with the type of gas indicated on the rating plate and may be installed in an aftermarket, permanently located, manufactured (mobile) home where not prohibited by local codes. Seeowner's manual for details.
Installer l'appareil selon les codes ou règlements locaux, ou, en l'absence de tels règlements, selon les codes d'installation ANSI Z223.1, National Fuel Gas Code ou CSA-B149.1 en vigueur.
Installer l'appareil selon la norme CAN/CSA-Z240, Série MM, Maison mobiles ou CAN/CSA-Z240 VC, Véhicules de camping, ou la norme 24 CFR Part 3280, Manufactured Home Construction and Safety
Standard. Si ces normes ne sont pas pertinentes, utilisez la norme ANSI/NCSBCS A225.1/NFPA 501A, Manufactured Home Installations Standard, ou ANSI A119.2 ou NFPA 501C Standard for Recreational
Vehicles.
Cet appareil doit être utilize uniquement avec le type de gaz indiqué sur la plaque signalétique. Cet appareil peut être installé dans une maison préfabriquée ou mobile (É.-U. seulement) installée à demeure si
les règlements locaux le permettent. Voir la notice de l'utilisateur pour plus de renseignements.
This vented gas fireplace heater is not for use with air filters.
Ne pas utiliser de filtre à air avec ce foyer au gaz à évacuation.
POUR UTILISATION UNIQUEMENT AVEC LES PORTES EN VERRE CERTIFIÉES AVEC L'APPAREIL
FOR USE WITH GLASS DOORS CERTIFIED WITH THE APPLIANCE ONLY.
Made in Canada/ Fabrique au Canada
NOT FOR USE WITH SOLID FUEL. / NE PAS UTILISER AVEC DU COMBUSTIBLE SOLIDE.
918-885a

For the State of Massachusetts, installation
and repair must be done by a plumber orgasfitter licensed in the Commonwealth of
Massachusetts.
For the State of Massachusetts, flexible connectors shall not exceed 36 inches in length.
For the State of Massachusetts, the appliances individual manual shut-off must be at-handle type valve.
The State of Massachusetts requires theinstallation of a carbon monoxide alarm inaccordance with NFPA 720 and a CO alarmwith battery back up in the same room where
the gas appliance is installed.

Regency Horizon HZ54E Gas Fireplace

5

REQUIREMENTS
MA Code - CO Detector(for the State of Massachusetts only)
5.08: Modifications to NFPA-54, Chapter 10(2) Revise 10.8.3 by adding the following additional requirements:(a) For all side wall horizontally vented gas fueled equipment installed in every dwelling, building or structure used in whole or in part forresidential purposes, including those owned or operated by the Commonwealth and where the side wall exhaust vent termination is less thanseven (7) feet above finished grade in the area of the venting, including but not limited to decks and porches, the following requirements shallbe satisfied:
1. INSTALLATION OF CARBON MONOXIDE DETECTORS. At the time of installation of the side wall horizontal vented gas fueled
equipment, the installing plumber or gasfitter shall observe that a hard wired carbon monoxide detector with an alarm and battery back-up is
installed on the floor level where the gas equipment is to be installed. In addition, the installing plumber or gasfitter shall observe that a battery
operated or hard wired carbon monoxide detector with an alarm is installed on each additional level of the dwelling, building or structure
served by the side wall horizontal vented gas fueled equipment. It shall be the responsibility of the property owner to secure the services ofqualified licensed professionals for the installation of hard wired carbon monoxide detectors
a. In the event that the side wall horizontally vented gas fueled equipment is installed in a crawl space or an attic, the hard wired carbon
monoxide detector with alarm and battery back-up may be installed on the next adjacent floor level.
b. In the event that the requirements of this subdivision can not be met at the time of completion of installation, the owner shall have a period ofthirty (30) days to comply with the above requirements; provided, however, that during said thirty (30) day period, a battery operated carbon
monoxide detector with an alarm shall be installed.
2. APPROVED CARBON MONOXIDE DETECTORS. Each carbon monoxide detector as required in accordance with the above provisions
shall comply with NFPA 720 and be ANSI/UL 2034 listed and IAS certified.
3. SIGNAGE. A metal or plastic identification plate shall be permanently mounted to the exterior of the building at a minimum height of eight(8) feet above grade directly in line with the exhaust vent terminal for the horizontally vented gas fueled heating appliance or equipment. The
sign shall read, in print size no less than one-half (1/2) inch in size, "GAS VENT DIRECTLY BELOW. KEEP CLEAR OF ALL
OBSTRUCTIONS".
4. INSPECTION. The state or local gas inspector of the side wall horizontally vented gas fueled equipment shall not approve the installation
unless, upon inspection, the inspector observes carbon monoxide detectors and signage installed in accordance with the provisions of 248 CMR
5.08(2)(a)1 through 4.
(b) EXEMPTIONS: The following equipment is exempt from 248 CMR 5.08(2)(a)1 through 4:
1. The equipment listed in Chapter 10 entitled "Equipment Not Required To Be Vented" in the most current edition of NFPA 54 as adopted by
the Board; and2. Product Approved side wall horizontally vented gas fueled equipment installed in a room or structure separate from the dwelling, building or
structure used in whole or in part for residential purposes.
(c) MANUFACTURER REQUIREMENTS - GAS EQUIPMENT VENTING SYSTEM PROVIDED. When the manufacturer of ProductApproved side wall horizontally vented gas equipment provides a venting system design or venting system components with the equipment, theinstructions provided by the manufacturer for installation of the equipment and the venting system shall include:
1. Detailed instructions for the installation of the venting system design or the venting system components; and2. A complete parts list for the venting system design or venting system.
(d) MANUFACTURER REQUIREMENTS - GAS EQUIPMENT VENTING SYSTEM NOT PROVIDED. When the manufacturer of a
Product Approved side wall horizontally vented gas fueled equipment does not provide the parts for venting the flue gases, but identifies"special venting systems", the following requirements shall be satisfied by the manufacturer:
1. The referenced "special venting system" instructions shall be included with the appliance or equipment installation instructions; and2. The "special venting systems" shall be Product Approved by the Board, and the instructions for that system shall include a parts list anddetailed installation instructions.
(e) A copy of all installation instructions for all Product Approved side wall horizontally vented gas fueled equipment, all venting instructions,
all parts lists for venting instructions, and/or all venting design instructions shall remain with the appliance or equipment at the completion of
the installation.

6

Regency Horizon HZ54E Gas Fireplace

DIMENSIONSUNIT DIMENSIONS
52-5/8” (1337mm)

59” (1499mm)

19-3/4” (502mm)

35-1/4” (895mm)

22-3/8” (568mm)
5-11/16”(144mm)46-3/8” (1178mm)

31-5/8” (803mm)

17-1/8” (435mm)

10-5/8”(270mm)48-1/2” (1232mm)

1-1/2”(38mm)

20-1/2” (521mm)

FACEPLATE & DOOR FRAME OVERLAY DIMENSIONS

Regency Horizon HZ54E Gas Fireplace

7

INSTALLATIONIMPORTANT MESSAGE
SAVE THESE
INSTRUCTIONSThe HZ54E Direct Vent Fireplace must be installedin accordance with these instructions. Carefully
read all the instructions in this manual first. Consult
the "authority having jurisdiction" to determine theneed for a permit prior to starting the installation.
It is the responsibility of the installer to ensure
this fireplace is installed in compliance with
manufacturers instructions and all applicable codes.

BEFORE YOU START
Safe installation and operation of this appliancerequires common sense, however, we are requiredby the Canadian Safety Standards and ANSIStandards to make you aware of the following:

INSTALLATION AND REPAIR SHOULD
BE DONE BY AN AUTHORIZEDSERVICE PERSON. THE APPLIANCESHOULD BE INSPECTED BEFORE
USE AND AT LEAST ANNUALLY BY A
PROFESSIONAL SERVICE PERSON.
MORE FREQUENT CLEANING MAY
BE REQUIRED DUE TO EXCESSIVE
LINT FROM CARPETING, BEDDING
MATERIAL, ETC. IT IS IMPERATIVETHATCONTROL COMPARTMENTS, BURNERS
AND CIRCULATING AIR PASSAGEWAYS
OF THE APPLIANCE BE KEPT CLEAN.
DUE TO HIGH TEMPERATURES, THE
APPLIANCE SHOULD BE LOCATEDOUT OF TRAFFIC AND AWAY FROMFURNITURE AND DRAPERIES.
WARNING: FAILURE TO INSTALL THISAPPLIANCE CORRECTLY WILL VOID
YOUR WARRANTY AND MAY CAUSE A
SERIOUS HOUSE FIRE.
CHILDREN AND ADULTS SHOULD BE
ALERTED TO THE HAZARDS OF HIGH
SURFACE TEMPERATURES, ESPECIALLY THE FIREPLACE GLASS, AND
SHOULD STAY AWAY TO AVOID BURNS
OR CLOTHING IGNITION.

YOUNG CHILDREN SHOULD BE CAREFULLY SUPERVISED WHEN THEY ARE
IN THE SAME AREA AS THE APPLIANCE. TODDLERS, YOUNG CHILDRENAND OTHERS MAY BE SUSCEPTIBLE
TO ACCIDENTAL CONTACT BURNS. A
PHYSICAL BARRIERS IS RECOMMENDED IF THERE ARE AT RISK INDIVIDUAL
IN THE HOUSE. TO RESTRICT ACCESSTO A FIREPLACE OR STOVE, INSTALL
AN ADJUSTABLE SAFETY GATE TO
KEEP TODDLERS, YOUNG CHILDRENAND OTHER AT RISK INDIVIDUALS OUT
OF THE ROOM AND AWAY FROM HOT
SURFACES.

CLOTHING OR OTHER FLAMMABLE
MATERIAL SHOULD NOT BE PLACEDON OR NEAR THE APPLIANCE.

GENERAL SAFETYINFORMATION

10) Be aware of electrical wiring locations in walls
and ceilings when cutting holes for termination.
11) Under no circumstances should this appliancebe modified. Parts that have to be removed forservicing should be replaced prior to operating
this appliance.
12) Installation and any repairs to this applianceshould be done by an authorized service person. A professional service person should becalled to inspect this appliance annually. Make
it a practice to have all of your gas appliances
checked annually.
13) Do not slam shut or strike the glass door.
14) Under no circumstances should any solid fuels(wood, paper, cardboard, coal, etc.) be used inthis appliance.
15) The appliance area must be kept clear andfree of combustible materials, (gases and otherflammable vapours and liquids).

Emissions from burning wood or gas could
contain chemicals known to the State ofCalifornia to cause cancer, birth defects orother reproductive harm.

1) The appliance installation must conform with local codes or, in the absence of local codes, withthe current Canadian or National Gas Codes,
CAN1-B149 or ANSI Z223.1 Installation Codes.
2) The appliance when installed, must be electrically grounded in accordance with local codes,
or in the absence of local codes with the current
National Electrical Code, ANSI/NFPA 70 or CSA
C22.1 Canadian Electrical Code.
3) See general construction and assembly instructions. The appliance and vent should be
enclosed.
4) This appliance must be connected to the specified vent and termination cap to the outside of
the building envelope. Never vent to anotherroom or inside a building. Make sure that thevent is fitted as per Venting instructions.
5) Inspect the venting system annually for blockage
and any signs of deterioration.
6) Venting terminals shall not be recessed into awall or siding.
7) Any safety glass removed for servicing must
be replaced prior to operating the appliance.
8) To prevent injury, do not allow anyone who isunfamiliar with the operation to use the fireplace.
9) Wear gloves and safety glasses for protection
while doing required maintenance.

8

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONINSTALLATIONCHECKLIST
1) Locate appliancea) Room location (Refer to "Locating Your Gas
fireplace" section)b) Clearances to Combustibles (Refer to"Clearances" section)c) Mantle Clearances (Refer to "Mantel
Clearances" section)d) Framing & Finishing Requirements (Refer
to "Framing & Finishing" section)e) Venting Requirements (Refer to "Venting"section)This includes:
1) Clocking the appliance to ensure the correct
firing rate (rate noted on label 41,500 Btu/h(NG), after burning appliance for 15 minutes.
2) If required, adjusting the primary air to ensurethat the flame does not carbon. First allow theunit to burn for 15-20 min. to stabilize.
CAUTION: Any alteration to the product thatcauses sooting or carboning that results in damage is not the responsibility of the manufacturer.

LOCATING YOURGAS FIREPLACE

2) Assemble Top and Side Standoffs (Refer to"Unit Assembly Prior to Installation).
3) Slide unit into place.
4) Install vent (Refer to "Venting Arrangement"
sections).
5) Make gas connections (Refer to "Gas Line
Installation section).
6) Install 4 AA batteries into battery pack.
7) Test the pilot (Refer to "Pilot Adjustment"
section).
8) Test Gas Pressure (Refer to "Gas Pipe Pressure
Testing" section).

1) When selecting a location for your fireplace,ensure that the clearances are met.
2) The appliance must be installed on a flat, solid,
continuous surface For example a wood, metal
or concrete floor or in a raised (on the wall) application. The appliance must be installed ona metal or wood panel extending the full widthand depth of the appliance.
3) The HZ54E Direct Vent Gas Fireplace can beinstalled in a recessed position or framed out
into the room as in A, B, C and D.
See Diagram 1.

9) Install standard and optional features. Refer tothe following sections:
a)
b)
c)
d)
e)
f)
g)
h)

5) The HZ54E Direct Vent Gas Fireplace
is approved for alcove installations, see"Clearances" section for details.
6) We recommend that you plan your installation
on paper using exact measurements forclearances and floor protection before actually
installing this appliance. Have an authorized
inspector, dealer, or installer review your plans
before installation.
Note: For vent terminations refer to "Exterior
Vent Termination Locations" section.

HEATWAVE
DUCT SYSTEMOPTIONAL KIT #946-556
The HeatWave Air Duct Kit increases theeffectiveness of your fireplace by dispersing warm
air from the fireplace to remote locations in the sameroom or other rooms in your home.
Up to two kits may be installed on the fireplace.

Optional Log Set Installation
Glass Crystals/ Optional Ceramic
Stones
Optional Firebox Base Pebbles
Optional Reflective Panels
Faceplate / Door Frame Overlay
Remote Control
Wall Thermostat
Wall Switch

Please Note: Only 1 HeatWave kit may be operated at one time. This includes the internal blower
option as well.

10) Final check.
Before leaving this unit with the customer, theinstaller must ensure that the appliance is firingcorrectly and operation fully explained tocustomer.

4) This appliance is Listed for bedroom
installations using the standard Remote(millivolt thermostat system). Some areas may
have further requirements, check local codes
before installation.

Diagram 1
A)
B)
C)
D)

Flat on Wall
Flat on Wall Corner
Recessed into Wall/Alcove
Corner

The HeatWave Duct Kit has different
clearance and framing requirements, checkthe HeatWave manual for details.

OPTIONAL
HEAT RELEASE KIT#946-570
The Heat Release Kit expels warm air from thefireplace to the outside of the building, allowing
the fireplace to be operated with less heat entering
the room. The kit may be used on either the leftor right side.

Regency Horizon HZ54E Gas Fireplace

9

INSTALLATION
CLEARANCESThe clearances listed below are Minimum distances unless otherwise stated:
A major cause of chimney related fires is failure to maintain required clearances (air space) to combustible materials. It is of the greatest importancethat this fireplace and vent system be installed only in accordance with these instructions.
Caution Requirements
The top, back and sides of the fireplace are defined bystandoffs. The metal ends of the standoff may NOT berecessed into combustible construction.

WARNING
Fire hazard is an extreme risk if these clearances (air space) to combustible materials
are not adhered to. It is of greatest importance that this fireplace and vent system beinstalled only in accordance with these instructions.

Clearance:

Dimension

Measured From:

A: Mantel Height (min.)20" (508mm)

Top of Fireplace Opening

B: Sidewall (on one side)4" (102mm)

Side of Fireplace Opening

The HeatWave Duct Kit and the Heat
Release Kit have different clearance
and framing requirements, check the
HeatWave and Heat Release manual
Heat Release Kit for details.

Flue Clearances to Combustibles

C: Ceiling(room and/or alcove)40-7/8" (1038mm)

D: Mantel Depth (max.)13" (330mm)

E: Alcove Width83" (2108mm)

Sidewall to Sidewall (Minimum)

F: Alcove Depth36" (914mm)

Front to Back Wall (Maximum)

G: To Floor

Top of Fireplace Opening
30" Above Fireplace Opening

28 - 7/8" (733mm)

Note

Horizontal - Top
Horiztonal - Side
Horiztonal - Bottom
VerticalPassing through wall/
floor/ceiling - whenfirestop is used.

Top of Fireplace Opening

0"

3"
2"
2"
2"

No hearth required

1-1/2"

C

D

F

F
B

A
B

G

E

Installed Close
to Ceiling

Installed Close
to Floor

NON-COMBUSTIBLE REQUIREMENTS
Metal Stud (header)60-1/2" (1537mm)

Wood Stud

3-7/8"( 99mm)10

Non-combustible

42-3/8” (1079mm)

22-5/8”Non-combustible

52-7/8”Material

Material

Non-combustible
Material

Non-combustible

22-1/2”(572mm)19-7/8"(505mm)Wood Stud

Material

5-1/2”(140mm)Regency Horizon HZ54E Gas Fireplace

INSTALLATIONNON COMBUSTIBLE FACING BOARD
All four pieces (top, 2 sides, bottom) are now supplied to meet the non combustible requirements. Previously only the top was supplied.

5-5/8”(143mm)21-3/4”52-5/8”Non-combustible Facing Board

Non-combustible
Facing Board
Non-combustible Facing Board

If finishing the wall above the unit with materials
such as tile, brick, marble, etc. non-combustible
board available from the building supply store
can be used.

Wood Stud

20"(508mm)Calcium silicate board is a high - grade material
with cement, quartz, natural and selectedminerals as the main raw materials. It is widelyused for partitions and ceilings in buildings.
It is fire proof and earthquake proof.

Metal Stud (header)61-1/2" (1537mm)
Wood Stud

22-3/8”(568mm)If finishing the wall above the unit with paint the non-combustible board (shipped separatelyfrom the unit) should be installed. Facing board
must be ordered when ordering the unit.

Non-combustible Facing Board

4"(102mm)Note: Calcium Silicate is 1/2' thick61-1/2" (1537mm)

NON COMBUSTIBLE FACING INSTALLATION
Caution: This non-combustible board can be damaged if
dropped or struck. Handle with care.
Inspect board prior to installation. Do not install if cracked.
1) Using drywall screws - secure non combustible material
around unit, framing and top nailing strip every 6 inches.
Important Note: To avoid cracking the board - pre-drill holes prior tosecuring to unit/ framing.
2) Wipe any debris/dust from the non combustible
material and drywall.
3) Prior to taping and mudding it is highly recommended
to prime the facing and edges using a quality primer. This will
ensure proper adhesion of both the tape and mud.
The optional board is very porous. During dry fit, ensue that both
surfaces being taped are even.

Non- combustible board(calcium silicate)Non- combustible board(calcium silicate)4) Tape the seams using a mesh type tape.
5) Mud seams as normal We recommend using a
product called Durabond high strength compound - for the first coat
This product can be found at any hardware store.
Mud must be cured as per manufacturer’s recommendations.
6) Prime wall for a second time for proper adhesion of paint7) Paint walls using a high quality paint which will withstandthe high temperatures being emitted from this appliance.
Note: Due to the high temperatures being emitted fromthis appliance, incorrectly mudded joints may crack. Keep mud
thickness to a minimum.

Regency Horizon HZ54E Gas Fireplace

Non-combustible board
MUST BE PRIMED.

11

INSTALLATIONMANTEL CLEARANCES
Due to the extreme heat this fireplace emits, the mantel clearances are critical. Combustible mantel clearances from top of front facing are shown in

Note: A non-combustible mantel may beinstalled at a lower height if the framing
is made of metal studs covered with a
non-combustible board.

6

4

2

0

14 12 10 8

the diagram on the right.

30
13" (330mm)

Combustible Material
3 ½" (89mm)

Note: Ensure the paint that is used on the mantel
and the facing is "heat resistant" or thepaint may discolour.

Drywall1" (25mm)

20

Metal Stud(On Edge)
Non-combustible
Facing

30”

10

21”

Standoff
20”0
Top of28-1/8” Fireplace

To UnitBase Legs

Opening

MANTEL LEG CLEARANCES
Combustible mantel leg clearances as per diagram:4”(102mm)

MANTEL LEG

7”

4"

Non-Combustible

Allowable mantel
leg projection

1.5" (38mm)

5-1/2” (140mm)
8” (203mm)

11” (279mm)

12

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONFRAMING & FINISHING
1) Frame in the enclosure for the unit with framing material.
IMPORTANT: Header must be metal stud. All other framing may be of
combustible type such as 2x4 / 2x6 framing materials.
ote: When constructing the framed opening, please ensure there is access to install the gas lines when the unit is installed.

6) Determine the total thickness of facing material (eg. hardiboard + ceramictile) to ensure the finished surface is flush with the front edge of theunit (see diagram below). If necessary, side and top nailing strips areadjustable, loosen the 1/4" screws and adjust.
Total non-combustible facing allowable: Min. = 1/2"
Max. = 1- 1/2"
See diagram below.

2) For exterior walls, insulate the enclosure to the same degree as the restof the house, apply vapour barrier and drywall, as per local installation
codes. (Do not insulate the fireplace itself.)
Important:

WARNING: Failure to insulate and add vapor barriers to the inside ofthe exterior wall will result in operational and performance problems
including, but not limited to: excessive condensation on glass doors,poor flame package, carbon, blue flames etc. These are not productrelated issues.

Finishedfacingmaterial to
be flush withedge of unit.

3) The unit does not have to be completely enclosed in a chase. You must
maintain clearances from the vent to combustible materials: See "Clearances" section. Combustible materials can be laid against the side andback standoffs and the stove base.
4) The combined total of non-combustible facing materials (ie. hardiboard+ tile, slate, etc) may be brought up to and overlap the face of the unit
(top and bottom). The minimum thickness = 1/2"
to a maximum thickness = 1-1/2", as shown in the diagram below.
If material is thicker than 1-1/2" - it will not be possible to mountthe faceplace.

5) When finishing around the faceplate, if material such as brick, stone, etc.
extend past the faceplate depth - the minimum opening
dimensions noted below must be adhered to, this is to ensure removalof the faceplate.

½”(13mm)
Min

Nailing Strips

1-1/2”(38mm)
Max

Finished
Material

Nailing Strip
Position

1/2"

1"
Nailing Strip
1” Forward

Unit
1"

1/2"
Nailing Strip½” Forward

For material such as brick, stone, etc that extends less than 1-1/2" , theminimum opening dimensions noted below must be adhered to whenfinishing around the unit. This is to ensure the removal of the faceplateand for the safe operation of this appliance.

Unit
1-1/2"0" (flush)

52-7/8 ”

22-5/8”

Nailing Strip
Flush w/unit
Factory Set

Unit
Unit shown without faceplate

Regency Horizon HZ54E Gas Fireplace

13

INSTALLATION
Framing
Dimensions

Description

HZ54E

A
B

Framing Height
Framing Width

46-5/8” (1184mm)
60” (1524mm)

C*
D
E
F
G
H
I
J
K
L

Framing Depth*
Minimum Height to Combustibles
Corner Wall Depth
Corner Facing Wall Width
Vent Centerline HeightNon-combustible facing heightGas Connection Opening HeightGas Connection HeightGas Connection Inset
Gas Connection Opening Width51” (1295mm)
72" (1829mm)
101-7/8 (2586mm)
44” (1118mm)
20” (508mm)
1-1/2” (38mm)
4” (102mm)
7-1/4” (184mm)
3-1/4” (83mm)

22” (559mm)* Framing depth measurement is noted with the side nailing strips set as far forward on the firebox as possible.
The side nailing strips can be adjusted back up to 1” to allow for varying thicknesses in non-combustible material & wall finishes.
Important: The minimum framing dimensions given for height, width and depth must be maintained even if
using non combustible materials.
Dangerous operating conditions will occur if minimum framing dimensions are not adhered to.

D

Metal Stud (Header)on edgeA

H

Metal Stud
(Header)on edge

Non-Combustible
Facing

B

G

C

E

I
J
K L

F
14

(Located on the right side of the fireplace)

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONNAILING STRIPS

UNIT ASSEMBLYPRIOR TO
INSTALLATIONThe Top Standoff/ Nailing Strip, side nailing strips and standoffs must be
correctly positioned and attached to the unit before sliding the unit into position.

The nailing strips come attached to the unit. There is 1 plate on each side,1on the top, and one on the bottom that can be folded out as required. The
top and side nailing strips are secured to the framing. The bottom nailingstrip is secured to the unfinished floor - if installing the unit directly on thefloor.
Note: The bottom nailing strip will need to be bent on site andadjusted to accommodate the thickness of the facing material.

STANDOFF ASSEMBLY
The top, side, rear and bottom standoffs are shipped in a flat position andmust be folded into shape and attached - see diagram 1.

Standoff

1) Remove the standoffs from the unit.
2) Take each standoff and bend into the correct shape. Bend up at the bendlines until the screw holes in the standoff and the pre-punched screw holeson the unit line up.

Standoff

Diagram 1

The top stand off / nailing strip is shipped attached to the back of the unit asshown below.
1) Remove one screw in location shown below.
Replace the screw on the back the unit after removing thestandoff / nailing strip.
2) Bend the 3 tabs at the bottom of the stand off / nailing strip to 90°,bend in the same direction as the top tabs.
3) Install on the top front of the unit as shown in diagram 3. Do not fullytighten the screws when installing - until the facing thickness has been
determined.

Nailing Strips

Diagram 3

IMPORTANT NOTE
Framing depth measurement is noted withthe side nailing strips set as far forward on
the firebox as possible. The nailing strips canbe adjusted back up to 1” to allow for varying
thicknesses in non-combustible material & wallfinishes.

VENTING INTRODUCTION
The HZ54E uses the "balanced flue" technology Co Axial system. The
inner liner vents products of combustion to the outside while the outer liner
draws outside combustion air into the combustion chamber thereby eliminating
the need to use heated room air for combustion and losing warm room air
up the chimney.
Note: These flue pipes must not be connected to any other appliance.
The gas appliance and vent system must be vented directly to the outside of
the building, and never be attached to a chimney serving a separate solid fuelor gas burning appliance. Each direct vent gas appliance must use it's own
separate vent system. Common vent systems are prohibited.

Standoff

Remove this screw torelease top standoff / nailing
stripStandoff

Regency Horizon HZ54E Gas Fireplace

Diagram 2

15

INSTALLATIONVENT RESTRICTOR POSITION
Vent restriction is required for certain venting installations, see the diagrams in the "Venting
Arrangements" section to determine if they are required for your installation.
The Vent Restrictor plate is located on the inside top of the firebox.
To set the vent restriction as indicated in the venting arrangements diagrams, refer to the following instructions;
1) Remove the glass door.
2) Remove the screws that hold the vent restrictor plate in place.
3) Adjust the vent restrictor plate to the required vent restrictor position as per the diagrams shown.
4) Once the vent restrictor plate is in the required position, secure with screws.

Vent Restrictor Settings for HZ54E-

Vent Restrictor Settings for HZ54E-LP

NG

SET 1
THIS HOLE SETS THE
VENT RESTRICTOR(factory setting)AT 4.25”

4.25”

SET 1
THIS HOLE SETS THE
VENT RESTRICTOR(factory setting)AT 4.25”

4.25”

Vent Restrictor Set 1

Vent Restrictor Set 1

Factory Set Vent Restrictor(No adjustment required)

Factory Set Vent Restrictor(No adjustment required)

3”
SET 2
THIS HOLE SETS THE
VENT RESTRICTOR
AT 3”

2”
SET 3
THIS HOLE SETS THE
VENT RESTRICTOR
AT 2”Vent Restrictor Set 2

Vent Restrictor Set 3

2”

1”

SET 3
THIS HOLE SETS THE
VENT RESTRICTOR
AT 2”

SET 4
THIS HOLE SETS THE
VENT RESTRICTOR
AT 1”

Vent Restrictor Set 3

Vent Restrictor Set 4
16

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONEXTERIOR VENT TERMINATION REQUIREMENTS

Minimum Clearance Requirements

Canada1

USA2

A

Clearance above grade, veranda, porch, deck, or balcony12"(30cm)

12"(30cm)

B

Clearance to window or door that may be opened

12"(30cm)

9" (23cm)

C

Clearance to permanently closed window

*

*

D

Vertical clearance to ventilated soffit located above the terminal within a horizontal distance of 2 feet (61cm)
from the center line of the terminal (check with the local code)24"(60cm)

24"(60cm)

E

Clearance to unventilated soffit

24"(60cm)

24"(60cm)

F

Clearance to outside corner: with AstroCap Termination Cap.

13"(33cm)

13"(33cm)

G

Clearance to outside corner: with all other approved Termination Caps.

13"(33cm)

13"(33cm)

Clearance to inside corner: with AstroCap Termination Cap

13"(33cm)

13"(33cm)

Clearance to inside corner: with all other approved Termination Caps.

13"(33cm)

13"(33cm)a

H

Clearance to each side of center line extended above meter/regulator assembly

36"(90cm)*

J

Clearance to service regulator vent outlet

36"(90cm)*

K

Clearance to non-mechanical air supply inlet to building or the combustion air inlet to any other appliance12"(30cm)

9" (23cm)

L

Clearance to a mechanical air supply inlet

72"(1.8m)

36"(90cm)b

M

Clearance above paved sidewalk or a paved driveway located on public property

84"(2.1m)┼*

Clearance under veranda, porch, deck, or balcony12"(30cm)‡*N
1

In accordance with current CSA B149.1, Natural Gas and Propane Installation Code2
In accordance with the current ANSI Z223.1/NFPA 54, National Fuel Gas Code┼A vent shall not terminate directly above a sidewalk or paved driveway which is located between two single family dwellings and serves both dwellings‡ Permitted only if veranda, porch, deck, or balcony is fully open on a minimum of two sides beneath the floor* Clearance in accordance with local installation codes and the requirements of the gas suppliera 3 feet (91cm) within a height of 15 feet (4.5m) above the meter / regulator assemblyb 3 feet (91cm) above - if within 10 feet (3m) horizontally

Regency Horizon HZ54E Gas Fireplace

17

INSTALLATIONVENTING ARRANGEMENTS
HORIZONTAL TERMINATION (FLEX)Regency® Direct Vent System
These venting systems, in combination with the HZ54E, have been tested and listed as a direct vent system by Warnock Hersey/Intertek. The location of thetermination cap must conform to the requirements in the Vent Terminal Locations diagram from the "Exterior Vent Termination Locations" section.
FPI Direct Vent (Flex) System Termination Kits include all the parts needed to install the HZ54E using a flexible vent.
Notes:
1) Liner sections should be continuous without any joints or
seams.

FPI Kit #Length Contains:#946-615

4 Feet#946-618#946-616

1) 8” flexible liner (Kit length)2) 5” flexible liner (Kit length)3) spring spacers
6 Feet 4) thimble
5) AstroCap termination cap
6) screws7) tube of Mill Pac
10 Feet8) plated screws9) S.S. screws #8 x 1-1/2” drill point
10) vinyl siding standoff

Vinyl SidingStandoff

Vent Guard - if required*(Part #946-506/P)

Wall Thimble(Mandatory in all
Horizontal Terminations)TM

AstroCap XL
Termination Cap(Part #946-623/P)

5” dia. flue pipe8” dia.
Flue pipe

spring spacer2) Only Flex pipe purchased from FPI may be used for Flex
installations.
3) Horizontal vent must be supported every 3 feet.
4) A wall thimble is mandatory for all horizontal terminations
due to high temperatures.

18

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONRIGID PIPE VENTING SYSTEMSBASIC HORIZONTAL & VERTICAL TERMINATIONS
Rigid Pipe Vent Systems offer a complete line ofcomponent parts for installation of both horizontal
and vertical installations. Many items are offeredin decorative black, as well as galvanized finish.
The minimum components required for a basic
Horizontal Termination are:Vertical Terminal
Storm Collar

Flashing

1
1
1
1
1

AstroCap XL Termination Cap
90o Elbow
Rigid Pipe Adaptor
Wall Thimble
Length of rigid pipe to suit wall thickness

The minimum components required for a basic
Vertical Termination are:
1
1
1
1
1
1

Ceiling Firestop
Vinyl SidingStandoff (Optional)
Pipe Length

AstroCap XL
Termination Cap(Part #946-623/P)

Pipe
LengthVertical Termination Cap
Rigid Pipe Adaptor
Lengths of pipe to adequately
penetrate roof
Ceiling Firestop
Flashing
Storm Collar

Vent Guard - if required*(Part #946-506/P)

Wall Thimble(Mandatory in all
Horizontal Terminations)

Pipe Lengtho

90 Elbow
Rigid Pipe
Adaptor (770-994)

Wall thickness is measured from the backstandoffs to the inside mounting surface oftermination cap. For siding other than vinyl, furring
strips may be used, instead of a vinyl siding
standoff, to create a level surface to mount thevent terminal. The Terminal must not be recessed
into siding. Measure the wall thickness including
furring strips.
If a Vinyl Siding Standoff is required (it must be
used with vinyl siding), measure to outside surface
of wall without siding and add 2 inches.

WARNING:

When using Rigid Vent other than
Simpson Dura-Vent, 3 screws must be
used to secure rigid pipe to adaptor.

Do not combine venting components fromdifferent venting systems.
Exception: However, use of the the AstroCap
XLTM is acceptable with all systems.
This product has been evaluated by Intertek forusing a Rigid Pipe Adaptor in conjunction with
Simpson DV Pro, Metal-Fab Sure-Seal, ICC
Excel and Selkirk Direct-Temp systems. Useof these systems with the Rigid Pipe adaptor
is deemed acceptable and does not affect the
Warnock Hersey/Intertek listing of components.

Alternate
Horizontal Termination
Caps
T

HO

Alternate Snorkel
Termination Cap

The FPI AstroCap XLTM is certified for installations using FPI venting systems as well as Simpson Dura-Vent® Direct Vent Pro, ICC Excel and Selkirk
Direct-Temp. AstroCap XLTM is a proprietary trademark of FPI Fireplace Products International Ltd. Dura-Vent® and Direct Vent are registered and/or
proprietary trademarks of Simpson Dura-Vent Co. Inc.

Regency Horizon HZ54E Gas Fireplace

19

INSTALLATION
5” X 8” RIGID PIPE CROSS REFERENCE CHART
Components from different Manufacturers may not be mixed. Not All Rigid Pipe components are available directly from FPI.
Description

SimpsonSelkirk

Metal-Fab™

ICC Excel

Direct Vent Pro®

Direct Temp™

Sure Seal

Direct6” Pipe Length-Galvanized

58DVA-06

5DT-6

5D6

TC-5DL6

6” Pipe Length-Black58DVA-06B

5DT-6B

5D6B

TC-5DL6B

9” Pipe Length-Galvanized

58DVA-09

5DT-9

N/A

N/A

9” Pipe Length-Black58DVA-09B

5DT-9B

N/A

N/A

12” Pipe Length-Galvanized

58DVA-12

5DT-125D12

TC-5DL1

12” Pipe Length-Black58DVA-12B

5DT-12B

5D12B

TC-5DL1B

18” Pipe Length-Galvanized

58DVA-18

5DT-185D18

TC-5DL18

18” Pipe Length-Black58DVA-18B - N/A from FPI

5DT-18B

5D18B

TC-5DL18B

24” Pipe Length-Galvanized

58DVA-24

5DT-245D24

TC-5DL224” Pipe Length-Black58DVA-24B

5DT-24B

5D24B

TC-4DL2B

36” Pipe Length-Galvanized

58DVA-36

5DT-36

5D36

TC-5DL3

36” Pipe Length-Black58DVA-36B

5DT-36B

5D36B

TC-5DL3B

48” Pipe Length-Galvanized

58DVA-48

5DT-485D48

TC-5DL4

48” Pipe Length-Black58DVA-48B

5DT-48B

5D48B

TC-5DL4B

60” Pipe Length-Galvanized

58DVA-60

N/A

N/A

N/A

60” Pipe Length-Black58DVA-60B - N/A from FPI

N/A

N/A

N/A

Adjustable Length 3”-10”-Galvanized

N/A

N/A

5DAL

TC-5DLT

Adjustable Length 3”-10”-Black

N/A

N/A

5DALB

TC-5DLTB

Adjustable Length 11”-14” -Galvanized

Disc. - See 58DV-08A

5DT-AJ

N/A

N/A

Adjustable Length 11”-14” -Black

Disc. - See 58DV-08B

5DT-AJB

N/A

N/A

Extension Pipe 17”-24” -Galvanized

Disc. - See 58DV-16A

N/A

N/A

N/A

Extension Pipe 17”-24” -Black

Disc. - See 58DV-16AB

N/A

N/A

N/A

Adjustable Length 8-1/2”-Galvanized

58DVA-08A - N/A from FPI

N/A

N/A

N/A

Adjustable Length 8-1/2”-Black58DVA-08AB

N/A

N/A

N/A

Extension Pipe 16”-Galvanized

58DVA-16A - N/A from FPI

N/A

N/A

N/A

Extension Pipe 16”-Black46DVA-16AB

N/A

N/A

N/A

45º Elbow-Galvanized

58DVA-E45

5DT-EL45

5DT-EL45

TE-5DE45

45º Elbow-Black58DVA-E45B

5DT-EL45B

5DT-EL45B

TE-5DE45B

45º Elbow Swivel-Galvanized

Disc. - See 58DVA-E45

N/A

N/A

N/A

45º Elbow Swivel-Black

Disc.-See 58DVA-E45B

N/A

N/A

N/A

90º Elbow-Galvanized

58DVA-E90

5DT-EL90S

5DT-EL90S

TE-5DE90

90º Elbow-Black58DVA-E90B

5DT-EL90SB

5DT-EL90SB

TE-5DE90B

90º Elbow, Swivel-Galvanized

Disc. - See 46DVA-E45

N/A

N/A

N/A

90º Elbow, Swivel-Black

Disc. - See 46DVA-E45

N/A

N/A

N/A

90º Starter Elbow, Swivel-Galvanized

N/A

N/A

N/A

N/A

Adaptor*

N/A

N/A

N/A

N/A

Ceiling Support

58DVA-DC

5DT-CS

5DSP

TE-5DE45

Cathedral Support Box

58DVA-CS

5DT-CSS

5DRS

TE-5DE45B

Wall Support/Band

58DVA-WS

5DT-WS/B

5DWS

N/A

Offset Support

58DVA-ES - N/A from FPI

5DT-OS

N/A

N/A

Wall Thimble-Black58DVA-WT

5DT-WT

5DWT

TE-5DE90

Wall Thimble Support/Ceiling Support

58DVA-DC - N/A from FPI

N/A

N/A

TE-5DE90B

Firestop Spacer

58DVA-FS

5DT-FS

5DFS

N/A

Trim Plate-Black58DAV-WFS

5DT-TP

5DCP

N/A

20

Regency Horizon HZ54E Gas Fireplace

INSTALLATION
Description

SimpsonSelkirk

Metal-Fab™

ICC Excel

Direct Vent Pro®

Direct Temp™

Sure Seal

DirectAttic Insulation Shield 12”

58DVA-IS N/A from FPI

N/A

N/A

N/A

Basic Horizontal Termination Kit (A)N/A

5DT-HKA

N/A

N/A

Horizontal Termination Kit (B)

58DVA-KHA

5DT-HKB

N/A

N/A

Vertical Termination Kit

58DVA-VHA

5DT-VKC

N/A

N/A

High Wind Vertical Cap

58DVA-VCH

N/A

N/A

TM-5VT

High Wind Horizontal Cap

N/A

N/A

N/A

TM-5DHT

Horizontal Square Termination Cap

N/A

5DT-HHC

5DHT

TM-5HT

Vertical Termination Cap

N/A

5DT-HVC

5DVT

TM-5VT

Storm Collar

58DVA-SC

5DT-SC

5DSC

TM-SC

Adjustable Flashing 0/12-6/12

58DVA-F6

5DT-AF65DF

TF-5FA

Adjustable Flashing 6/12-12/12

58DVA-F12

5DT-AF125DF1-2

TF-5FB

Vinyl Siding Standoff

58DVA-VSS

5DT-VS

5DVS

TM-VSS

Vinyl Siding Shield Plate

N/A

5DT-VSP

N/A

N/A

Snorkel Termination 14”

58DVA-SNK14

N/A

N/A

TM-5ST14

Snorkel Termination 36”

58DVA-SNK36 (N/A - FPI)

N/A

N/A

TM-5ST36

Restrictor Disk

58DVA-RD

N/A

N/A

TM-5DS

Colinear Flex Connectors

N/A

N/A

N/A

N/A

FPI
946-604/P

Simpson Direct Vent -Vent Guard (Optional)

946-623/P

AstroCap XL Horizontal Cap

770-994

Rigid Pipe Adaptor (Must use with all rigid piping)

946-506/P

Vent Guard (Optional)

946-606

Starter collar reducer 5” x 8” to 4” x 6-5/8”

946-625

Vinyl Siding Standoff - AstroCap XL

Note: When using Metal-Fab Sure Seal Rigid Piping - please note that the Adaptor (4DDA) must be used in conjunction with FPI Rigid Pipe Adaptor (510-994).
Offset Pipe Selection: Use this table to determine offset pipe lengths.
Pipe Length(L)5” x 8” Venting
Run (X)

Rise (Y)For specific instructions on venting components - visit the
manufacturers website listed below.

0” (0mm)5-11/16” (144mm)

15-5/16” (389mm)

6” (152mm)

8-13/16” (224mm)

18-7/16” (468mm)

Selkirk Direct-Temp: www.selkirkcorp.com

9” (229mm)

10-15/16” (278mm)

20-9/16” (522mm)

Metal-Fab Sure Seal: www.mtlfab.com

12” (305mm)

13” (330mm)

22-11/16” (576mm)

Industrial Chimney Company: www.icc-rsf.com

24” (610mm)

21-7/16” (697mm)

31-1/16” (789mm)

36” (914mm)

29-13/16” (757mm)

39-7/16” (1002mm)

48” (1219mm)

38-1/4” (972mm)

47-7/8” (1216mm)

Note: Horizontal runs of vent must be level, or have a 1/4”
rise for every 1 foot of run towards the termination.
Never allow the vent to run downward - this could cause hightemperatures and may present a possible fire hazard.

Regency Horizon HZ54E Gas Fireplace

Simpson Direct Vent Pro: www.duravent.com

21

INSTALLATIONVENTING ARRANGEMENTS
ALLOWABLE HORIZONTAL TERMINATIONS FOR HZ54E-NG

VENTING ARRANGEMENTS
ALLOWABLE HORIZONTAL TERMINATIONS FOR HZ54E-LP
The diagram shows all allowable combinations of vertical runs with horizontal
terminations, using one 90o (two 45o elbows equal one 90o elbow).

The diagram shows all allowable combinations of vertical runs with horizontal
terminations, using one 90o (two 45o elbows equal one 90o elbow).

Note: Must use optional rigid pipe adapter (Part# 770-994) when using
Rigid Pipe Venting Systems.

Note: Must use optional rigid pipe adapter (Part# 770-994) when using
Rigid Pipe Venting Systems.

Horizontal (Feet)
0

2

4

6

8

10

12

14

16

18

20

18

Horizontal (Feet)
Vent Restrictor
on Set 3

0

2

4

6

8

10

12

14

16

18

20

18

16

16

14

14

12

Vent Restrictor
on Set 3
10Vent Restrictor
on Set 1(factory setting)8

6

Vertical Height (Feet)

Vertical Height (Feet)

Vent Restrictor
on Set 2

12

10Vent Restrictor
on Set 1(factory setting)

8

4

6

2

44” (1118mm)
Minimum Height
Requirement

4

0

2

44” (1118mm)
Minimum Height
Requirement

0

VENT RESTRICTOR SETTING:
Vent restrictor factory set, no adjustment required unless otherwise
indicated.
Refer to the "Vent Restrictor Position" section for details on how tochange the vent restrictor from the factory setting of Set 1 to Set 2 orSet 3 if required.

VENT RESTRICTOR SETTING:
Vent restrictor factory set, no adjustment required unless otherwise
indicated.
Refer to the "Vent Restrictor Position" section for details on how to change thevent restrictor from the factory setting of Set 1 to Set 3 if required.

Note: Regency® Direct Vent System (Flex) is only approved forhorizontal terminations.

Note: Regency® Direct Vent System (Flex) is only approved for horizontal
terminations.

•

•
•
•

Maintain clearances to combustibles as listed in "Clearances"sectionHorizontal vent must be supported every 3 feet.
Firestops are required at each floor level and whenever passing
through a wall.
A wall thimble is mandatory for all horizontal terminations due
to high temperatures.

•
•
•

22

•

Maintain clearances to combustibles as listed in "Clearances" section
Horizontal vent must be supported every 3 feet.
Firestops are required at each floor level and whenever passing
through a wall.
A wall thimble is mandatory for all horizontal terminations due tohigh temperatures.

Regency Horizon HZ54E Gas Fireplace

INSTALLATION
Horizontal Venting with Two (2) 90o Elbows
NG and LP

H1
V

H
o

o

One 90 elbow = Two 45 elbows.

OptionV

H + H1A)

2' Min.

4' Max.

B)

3' Min.

6' Max.

C)

4' Min.

8' Max.

D)

5' Min.

9' Max.

E)

6' Min.

10' Max.

With these options,maximum total pipe
length is 30 feet withminimum of 6 feet total
vertical and maximum
10 feet total horizontal.

Please note minimum 1 foot between 90o elbows is
required.
VENT RESTRICTOR SETTING:
Vent restrictor factory set at Set 1, no adjustment
required.

Horizontal Venting with Three (3) 90o Elbows
NG and LP

H1

HV1
One 90o elbow = Two 45o elbows.

Option
A)
B)
C)
D)
E)
F)

V
2' Min.
2' Min.
3' Min.
4' Min.
5' Min.
6' Min.

H
1' Max.
2' Max.
2' Max.
3 Max.
4' Max.
6' Max.

V + V1
3' Min.
5' Min.
7' Min.
9' Min.
10' Min.
11' Min.

H + H12' Max.
4' Max.
5' Max.
6' Max.
7' Max.
9' Max.

V

With these options, max.
total pipe length is 30 feetwith min. of 11 feet total
vertical and max. 9 feet total
horizontal.
Please note min. 1 footbetween 90 o elbows is
required.

VENT RESTRICTOR SETTING:
Vent restrictor factory set at Set 1, no adjustment required.

Regency Horizon HZ54E Gas Fireplace

23

INSTALLATION
Vertical Venting with Three (3) 90o Elbows
NG and LP

One 90o elbow = Two 45o elbows.

Option
A)
B)
C)
D)
E)

V
2' Min.
3' Min.
4' Min.
5' Min.
6' Min.

H + H1 V + V1
2' Max. 4' Min.
4' Max. 6' Min.
5' Max. 7' Min.
6' Max. 8' Min.
8' Max. 9' Min.

With these options, max. total
pipe length is 30 feet with min.
of 9 feet total vertical and max.
8 feet total horizontal.
Please note min. 1 footbetween 90 o elbows is
required.

VENT RESTRICTOR SETTING:
Vent restrictor factory set at Set 1, no adjustment required.

V1

H1

24

H

V

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONVENTING ARRANGEMENTS
ALLOWABLE VERTICAL TERMINATIONS FOR HZ54E-NG

The shaded area in the diagram shows all allowablecombinations of straight vertical and offset to verticalterminations, using two 90o elbows, with Rigid Pipe Venting
Systems for Natural Gas. Two 45o elbows equal to one 90o
elbow. Maximum of four 45o elbows allowed.

Horizontal (Feet)
0

2

4

6

8

10

12

14

16

40

Maximum: 40 ft. (12.2m)

38

36

34

32

30

Vent Restrictor on Set 3
28

26

24

Vent Restrictor on Set 2

20

Maximum: 27 ft. (8.2m)

Vertical Height (Feet)

22

18

16

14

Please note min. 1 foot between 90oelbows is required.
12•

Note: Must use optional flue adaptor when using
Rigid Pipe (Part # 770-994).

Vent Restrictor on Set 1(factory setting)
10

8

6

4

2

Minimum
8’6” (2.6m)•

Vent must be supported at offsets.
Firestops are required at each floor level andwhenever passing through a wall.
Maintain clearances to combustibles as listed inthe "Clearances" section.
Refer to the "Vent Restrictor Position" section
for details on how to change the vent restrictor
from the factory setting of Set 1 to Set 2 or Set 3
if required.

Min. 44”(1118mm)••0

Minimum length of pipe
between elbows 12” (305mm)

Regency Horizon HZ54E Gas Fireplace

Max. 10’ (3m)(centerline to centerline)

25

18

20

INSTALLATIONVENTING ARRANGEMENTS
ALLOWABLE VERTICAL TERMINATIONS FOR HZ54E-LP
Horizontal (Feet)

The shaded area in the diagram shows all allowablecombinations of straight vertical and offset to verticalterminations, using two 90o elbows, with Rigid Pipe Venting
Systems for Propane. Two 45o elbows equal to one 90o
elbow. Maximum of four 45o elbows allowed.

0

2

4

8

6

10

12

14

16

18

40

Maximum: 40 ft. (12.2m)

38

36

34

32

30

Vent Restrictor on Set 4
28

26

24

Vent Restrictor on Set 3

20

Maximum: 27 ft. (8.2m)

Vertical Height (Feet)

22

18

16

14

Please note min. 1 foot between 90oelbows is required.

12

Vent Restrictor on Set 1(factory setting)10•

Note: Must use optional flue adaptor when using
Rigid Pipe (Part # 770-994).

8

6

4

2

Minimum
8’6” (2.6m)•

Vent must be supported at offsets.
Firestops are required at each floor level andwhenever passing through a wall.
Maintain clearances to combustibles as listed inthe "Clearances" section.
Refer to the "Vent Restrictor Position" section
for details on how to change the vent restrictor
from the factory setting of Set 1 to Set 3 or Set 4
if required.

Min. 44”(1118mm)••0Max. 10’ (3m)(centerline to centerline)
Minimum length of pipe
between elbows 12” (305mm)

26

Regency Horizon HZ54E Gas Fireplace

20

INSTALLATION
7) Ensure that the pipe clearances to combustible
materials are maintained (Diagram 5). Install
the termination cap.

UNIT INSTALLATIONWITH HORIZONTALTERMINATION

Note: If installing termination on a vinyl siding
covered wall, a vinyl siding standoff or
furring strips must be used to ensurethat the termination is not recessed into
the siding.

(Rigid Vent Systems)
Diagram 1
A top clearance of 3"(76mm) and side & bottom
clearance of 2"(51mm) must be maintained;
except when passing through a wall, ceiling, orat the termination where the use of a firestop
or wall thimble reduces the required clearance
to 1-1/2" (38mm). We recommend framing a11"(279mm) x 11"(279mm) (inside dimensions)hole to give structural rigidity for mounting thetermination.
Install the vent system according to the manufacturer's
instructions included with the components.
1) Set the unit in its desired location. Check todetermine if wall studs or roof rafters are in
the way when the venting system is attached.
If this is the case, you may want to adjust thelocation of the unit. Rough in the gas preferablyon the right side of the unit.
2) Direct Vent pipe and fittings are designed withspecial twist-lock connections to connect theventing system to the appliance flue outlet. A
twist-lock appliance adaptor is required.

Horizontal runs of vent must be supported every
3 feet (0.9meter). Wall straps are available forthis purpose.

6) Mark the wall for a 11" x 11" (279mm x 279mm)
square hole. The center of the square holeshould line up with the center-line of thehorizontal pipe. Cut and frame the 11 inch
(279mm) square hole in the exterior wall wherethe vent will be terminated. See diagram 2 forcenter line requirements.
If the wall being penetrated is constructed of
non-combustible material, i.e. masonry block
or concrete, an 8" (203mm) diameter hole isacceptable.
Diagram 5
The four wood screws provided should be
replaced with appropriate fasteners for stucco,
brick, concrete, or other types of sidings.

3) In conjunction with the Simpson Direct Vent
Pro system, install the adaptor after the unit isset in its desired location. Put a bead of hightemperature silicone inside the outer sectionof the adapter and a bead of Mill Pack on the
inner collar. Slip the adapter over the existing
inner and outer flue collar. Fasten to the outercollar only with the 3 supplied screws (drilling
pilot holes will make this easier).

8) Before connecting the horizontal run of vent pipe
to the vent termination, slide the Wall Thimble
over the vent pipe. The wall thimble is required
for all horizontal terminations.
9) Slide the appliance and vent assembly towards
the wall carefully inserting the vent pipe into thevent cap assembly. It is important that the ventpipe extends into the vent cap sufficient distanceso as to result in a minimum pipe overlap of
1-1/4 inches (32mm). Secure the connection
between the vent pipe and the vent cap.

4) Level the fireplace and fasten it to the framing
using nails or screws through the top and side
nailing strips.
5) Assemble the desired combination of pipe andelbows to the appliance adaptor and twist-lockfor a solid connection.

Diagram 2

Note: Forbestresultsandoptimumperformancewith each approved venting system, it ishighly recommended to apply “Mill-Pac”
sealant (supplied) to every inner pipe
connection. Failure to do so may resultin drafting or performance issues notcovered under warranty. Silicone (redRTV) is optional.

Note:a) The horizontal run of vent must be level, or
have a 1/4 inch rise for every 1 foot of run
towards the termination. Never allow thevent to run downward. This could cause
high temperatures and may present thepossibility of a fire.
b) The location of the horizontal venttermination on an exterior wall must meet
all local and national building codes, andmust not be blocked or obstructed. See"Exterior Vent Termination Locations"section for more details.

Regency Horizon HZ54E Gas Fireplace10) Install wall thimble in the center of the 11"(279mm) square and attach with wood screws(Diagram 7).

Diagram 7

27

INSTALLATIONUNIT INSTALLATIONWITH VERTICALTERMINATION(Rigid Vent Systems)
Note: A clearance of 2"(51mm) must be
maintained; except when passing
through a wall, ceiling, or at thetermination where the use of a firestop
or wall thimble reduces the required
clearance to 1-1/2" (38mm). We
recommend framing a 11"(279mm) x
11"(279mm) (inside dimensions) hole
to give structural rigidity for mounting
the termination.
1) Maintain the 1-1/2" (38mm)
clearances (air spaces)
to combustibles when
passing through ceilings,
walls, roofs, enclosures,
attic rafter, or other nearby
combustible surfaces,
ensuring that the use ofa firestop or wall thimble
is used as noted above.
Do not pack air spaces
with insulation. Check"Venting Arrangement- Vertical Termination"section for the maximum
vertical rise of the venting
system and the maximum
h o r i z o n t a l o ff s e tlimitations.

4) Assemble the desired lengths of pipe and elbows.
Ensure that all pipes and elbow connections arein the fully twist-locked position and sealed.

Note:
For best results and optimum performancewith each approved venting system, it is highly
recommended to apply “Mill-Pac” sealant toevery inner pipe connection. Failure to do so
may result in drafting or performance issues
not covered under warranty. Silicone (red RTV)
is optional.

5) Cut a hole in the roof centered on the small
drilled hole placed in the roof in Step 2. The holeshould be of sufficient size to meet the minimum
requirements for clearance to combustibles of
1-1/2"(38mm). Slip the flashing under the shingles(shingles should overlap half the flashing) as per
Diagram 4.

Diagram 5

Roof Pitch

Minimum Vent
HeightFeet

Metersflat to 7/12

2

0.61

over 7/12 to 8/12

2

0.61

over 8/12 to 9/12

2

0.61

over 9/12 to 10/12

2.5

0.76

over 10/12 to 11/12

3.25

0.99

over 11/12 to 12/12

4

1.22

over 12/12 to 14/12

5

1.52

over 14/12 to 16/12

6

1.83

over 16/12 to 18/12

7

2.13

over 18/12 to 20/12

7.5

2.29

over 20/12 to 21/12

8

2.44

A poor draft, or down drafting can result from highwind conditions near big trees or adjoining rooflines, in these cases, increasing the vent height
may solve the problem.

Diagram 1

2) Set the gas appliancein its desired location.
Drop a plumb bob
down from the ceilingto the position of theappliance flue exit,
and mark the location
where the vent will
penetrate the ceiling.
Drill a small hole at
his point. Next, dropa plumb bob fromthe roof to the hole
Diagram 2previously drilled in the ceiling, and mark the spot
where the vent will penetrate the roof. Determine
if ceiling joists, roof rafters or other framing will
obstruct the venting system. You may wish to
relocate the appliance or to offset, as shown in
Diagram 2 to avoid cutting load bearing members.
3) A Firestop spacer must be installed in the floor
or ceiling of every level.

7) Ensure vent is vertical and secure the base of
the flashing to the roof with roofing rails, slide
storm collar over the pipe section and seal witha mastic.
8) Install the vertical termination cap by twistlocking it.
Note: Any closets or storage spaces, which thevent passes through must be enclosed.
Diagram 4: The upper half of the flashing isinstalled under the roofing material and not
nailed down until the chimney is installed.
This allows for small adjustments.

Offset Chart

6) Continue to assemble pipe lengths.
Note: If an offset is necessary in the attic toavoid obstructions, it is important tosupport the vent pipe every 3 feet (0.9meter), to avoid excessive stress on theelbows, and possible separation. Wallstraps are available for this purpose(Diagram 2).
Galvanized pipe is desirable above the roofline
due to its higher corrosion resistance. Continue
to add pipe sections through the flashing until
the height of the vent cap meets the minimum
height requirements specified in Diagram 5 or
local codes. Note that for steep roof pitches, thevertical height must be increased.

Diagram 3
28

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONUNIT INSTALLATIONHORIZONTAL TERMINATIONWITH FLEX VENT SYSTEM
Note: A top clearance of 3"(76mm) andside & bottom clearance of 2"(51mm)
must be maintained; except when
passing through a wall, ceiling, or at
the termination where the use of afirestop or wall thimble reduces therequired clearance to 1-1/2" (38mm).
We recommend framing a 11"(279mm)
x 11"(279mm) (inside dimensions) hole
to give structural rigidity for mounting
the termination.
1) Locate the unit in the framing, rough in the gas(preferably on the right side of the unit). Locate
the centerline of the termination and mark wall
accordingly. Cut an 11"(279mm) hole in the wall(inside dimension).

4) Separate the 2 halves of the wall thimble andsecurely fasten the one with the tabs to theoutside wall making sure that the tabs are on
top and bottom. Fasten the other thimble half
to the inside wall. The thimble halves slip insideeach other and can be adjusted for 2 x 4 or 2 x
6 walls.
5) Slip the assembled liner and terminationassembly through the thimble making sure thetermination cap faces up (there are markings
on the cap that show which way is up). This will
position the termination cap with proper downslope for draining water. Fasten the cap to theouter wall with the 4 supplied screws.

IMPORTANT: Do not locate termination hood
where excessive snow or ice buildup may
occur. Be sure to check vent termination
area after snow falls, and clear to prevent
accidental blockage of venting system. Whenusing snow blowers, make sure snow is notdirected towards vent termination area.

ASTROCAP XLDIMENSIONS (946-623/P)

6) Pull the centre 5"(127mm) liner and outer
8"(203mm) liner out enough to slip over the flue
collars of the fireplace. (You may wish to cut
the liner shorter to make it more workable.) Do
not bend liner more than 90o. The liners mustslip over the collars a minimum of 1-3/8".

7) Apply Mill Pac over the fireplace inner collar
and slip the 5"(127mm) liner down over it andattach with 3 supplied screws.
8) Do the same with the 8"(203mm) liner.
9) Apply a bead of silicone between the thimble
and termination and around the outer edge ofthe terminal at the wall in order to keep the waterout.

Note: If installing termination on a siding covered wall, a vinyl siding standoff or vinyl
furring strips must be used to ensure thatthe termination is not recessed into thesiding.
2) Level the fireplace and fasten it to the framing
using nails or screws through the nailing strips.
3) Assemble the vent assembly by applying Mill
Pac to the 5"(127mm) inner collar of the termination and slipping the 5"(127mm) liner over it atleast 1-3/8" (35mm). Fasten with the 3 screws(drilling pilot holes will make this easier). Apply Mill Pac or high temperature silicone to the8"(203mm) flex pipe and slip it over the 8" outercollar of the vent terminal at least 1-3/8"(35mm)
and fasten with the 3 screws.
NOTE:

Horizontal sections must be supported
at intervals not exceeding 3 feet (0.9meter). (Flame picture and performance
will be affected by sags in the liner).

Regency Horizon HZ54E Gas Fireplace

29

INSTALLATION
1) Make sure the valve is in the "OFF" position.

HZ54E-NG SYSTEM DATA
Min. Supply Pressure

5" WC (1.25 kpa)

Low Setting Man.
Pressure

1.6" WC (0.40kpa)

Max. Manifold
Pressure

3.5" WC (0.87 kpa)

Orifice Size

#30 DMS

Minimum Input

29,000 Btu/h(8.50 kW)

Maximum Input

41,500 Btu/h(12.16 kW)

2) Loosen the "IN" and/or "OUT" pressure tap(s),turning counterclockwise with a
1/8" wide flat screwdriver.
3) Attach manometer to "IN" and/or "OUT" pressuretap(s) using a 5/16" ID hose.
4) Light the pilot and turn the valve to "ON" position.
5) The pressure check should be carried out withthe unit burning and the setting should be within
the limits specified on the safety label.
6) When finished reading manometer, turn off thegas valve, disconnect the hose and tighten thescrew (clockwise) with a 1/8" flat screwdriver.
Note: Screw should be snug, but do not overtighten.

HZ54E-LP SYSTEM DATA
Min. Supply Pressure

12" WC (2.98 kpa)

Low Setting Man.
Pressure

6.4" WC (1.59kpa)

Max. Manifold
Pressure

10" WC (2.49 kpa)

Orifice Size

#49 DMS

Minimum Input

30,000 Btu/h(8.79 kW)

Maximum Input

37,000 Btu/h(10.84 kW)

PILOT ADJUSTMENT
Periodically check the pilot flames. Correct flame
pattern has two strong blue flames: 1 flowing
around the flame sensor and 1 flowing acrossthe burner (it does not have to be touching theburner).

BurnerHIGH ELEVATION

Flame Sensor

This unit is approved for altitude 0 to 4500 ft.
(CAN1 2.17-M91).

Pilot

GAS LINE
INSTALLATION
Since some municipalities have additional
local codes it is always best to consult withyour local authorities and the CAN/CGA B149
installation code.
For USA installations follow local codes and/or the current National Fuel Gas Code, ANSI
Z223.1.
When using copper or flex connectors use only
approved fittings. Always provide a union sothat gas lines can be easily disconnected forservicing. Flare nuts for copper lines and flex
connectors are usually considered to meet thisrequirement.
NOTE: A shutoff / dante valve should be
supplied in or near the unit (or as per local
codes) for ease of servicing this appliance.
IMPORTANT: Always check for gas leaks witha soap and water solution or gas leak detector. Do not use open flame for leak testing.

886 S.I.T. VALVEDESCRIPTION
1)
2)
3)
4)
5)
6)
7)

Manual high/low adjustment
Pilot adjustment
Outlet Pressure Tap
Inlet Pressure Tap
Pilot Outlet
Main Gas Outlet
Main Gas Inlet

Ignitor

Note: If you have an incorrect flame pattern,
contact your Regency® dealer for further
instructions.

3

4

Incorrect flame pattern will have small, probably
yellow flames, not coming into proper contact
with the rear burner or flame sensor.

GAS PIPE PRESSURETESTING

2

1

The appliance must be isolated from the gas supply piping system by closing its individual manual
shut-off valve during any pressure testing of thegas supply piping system at test pressures equal
to or less than 1/2 psig. (3.45 kPa). Disconnect
piping from valve at pressures over 1/2 psig.
The manifold pressure is controlled by a regulator
built into the gas control, and should be checkedat the pressure test point.
Note: To properly check gas pressure, both
inlet and manifold pressures should bechecked using the valve pressure portson the valve.

7

5
6

30

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONVALVE COVER REMOVAL
The valve cover will need to be removed to access the valve tray (see valve
tray replacement) and also to access the DBFC (see Battery + ON/OFF
switch installation).

4) Lift the cover up off the screws and out of the unit.
5) To install - reverse steps.

1) Remove Faceplate and glass door if installed.
2) The valve cover is located on the right side underneath the glass door loosen 2 screws securing the valve cover (see Diagram 1 below).

Diagram 3

Valve cover

Diagram 1

3) Slide the valve cover upward.

Diagram 2

Regency Horizon HZ54E Gas Fireplace

31

INSTALLATIONAERATION ADJUSTMENT
The burner aeration is factory set but may needadjusting due to either the local gas supply or
altitude. Open the air shutter for a blue flame orclose for a more yellow flame.

Minimum Air Shutter Opening:
NG
1/2"
LP
1/2"
LP w/Logs = Full OpenFor instructions to remove the burner for access tothe ventury cap, see pages 46-47 in this manual.

CAUTION: Carbon will be produced if air shutter
is tightly closed.
Note: Any damage due to carboning
resulting from improperly setting
the aeration controls is NOT covered
under warranty.

Venturi Cap

WIRING DIAGRAMThis heater does not require a 120V A.C. supply for operation. In case of a power failure, the burner switch and the optional remote control/thermostat willcontinue to operate. However, a 120V A.C. power supply is needed for the fan/blower operation.
(Do not cut the ground terminal off under any circumstances.)
NOTE: Even if the fan is not purchased with the unit, it is still a good idea to bring power to the receptacle box (provided with the unit) in case thefan is installed at a later date.

SureFire™ Switch

0.886.001
Proflame Valve

Standard Main On/Off Switch
or Optional Wall Switch

Note: 4 AA batteries must be installed to operate
the burner switch.
Do not use a 9 volt battery.
IMPORTANT: If the optional remote control is used, the AA batteries normally installed into the battery holder must be removed. The AA batteries in thereceiver now operate the unit. Having AA batteries in both the battery holder and receiver will damage the gas valve.

32

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONPROFLAME SYSTEM GTMF WITH OPTIONAL FAN

Proflame System
Configuration
885 GTMF
886
Wire Diagram

SureFire™ Switch

Fan

GroundNeutral120V AC
60 Hz

Live

Black
Ground

Black

White
Black

Green
Black

Black

Fan Thermodisc(normally open)

Regency Horizon HZ54E Gas Fireplace

33

INSTALLATIONOPTIONAL FAN WIRING DIAGRAMWITHOUT PROFLAME GTMF SYSTEM

Lockwasher
Star washer

Fan

Ground#8 Ground Lug(for mobile home)Black

Neutral120V AC
60 Hz

Live

White
Black

Green

Ground

Black

Black

Black

Fan Thermodisc(normally open)

Nut
Fanground wire

NOTE: Wiring schematics for HZ54E (120 Volts),
plug-in fan circuit with speed control switch on wall.

Electrical Connection Alternative Scheme "A",Power at Stove

Electrical Connection Alternative Scheme "B",Power at Switch
Wall Junction Box

Wall Junction Box~

Wire Nuts*Speed Control
Switch withlead wires(Regency)~*Speed Control
Switch with lead wires
Wire Nuts

Black (Hot)
120 Volts White (Neutral)
60 Hz Copper Ground
Wire

14 AWG wire
*Wire Clamp*Receptacle Box
inside stove*Receptacle(dedicated use
by stove fan only)

Copper Ground
120 Volts White (Neutral)
60 Hz
Black (Hot)
14 AWG wire

Wire Nuts

Black
White
Ground14 AWG wire

*Wire Clamp* = supplied with fan kit*Receptacle Box
inside stove

Other parts are to be suppliedby electrician or installer*Receptacle(dedicated use
by unit fan only)

Caution: Ensure that the wires do not touch any
hot surfaces and are away from sharp edges.

34

Regency Horizon HZ54E Gas Fireplace

INSTALLATION
Optional
WALL THERMOSTATA wall thermostat may be installed if desired,connect the wires as per the wiring diagram. Usetable below to determine the maximum wire length.
Note: Preferable if the thermostat is installedon an interior wall.

Optional
REMOTE CONTROL®

Use the Regency Remote Control Kit approved
for this unit. Use of other systems may void yourwarranty.
The remote control kit comes with a hand heldtransmitter, a receiver and a wall mounting plate.

Regency offers an optional programmablethermostat but any 250-750 millivolt rated nonanticipator type thermostat that is CSA, ULC or
UL approved may be used.

1) Choose a convenient location on the wall to
install the receiver and the receptacle box(protection from extreme heat is very important).
Run wires from the fireplace to that location.
Use Thermostat Wire Table.

CAUTION
Do not wire millivolt
wall thermostat wires
to 120V wire.

CAUTION
Do not wire millivolt
remote control wires
to 120V wire.

®

Thermostat Wire Table
Recommended Maximum Lead Length(Two-Wire) When Using Wall
Thermostat (CP-2 System)
Wire Size

14 GA.
16 GA.
18 GA.
20 GA.
22 GA.

Max. Length

WALL SWITCH(Included with Unit)
1) Run the supplied 10' of wire through the rightor left side gas inlet opening. Be careful not todamage wire.
Note: We recommend a maximum of 10' of wire
but if you wish to go with a longer run,use the Thermostat Wire Table.
2) Connect the wire to the wall switch and install
into the receptacle box (supplied). Also attach
wires to the valve as shown below.

CAUTION
Do not wire millivolt
wall switch wire
to 120V wire.

2) Connect the two wires to the IPI wire harness.See wiring diagrams. Optional wall switch GT/
GTM suing wire 0.584.907.

3) Install 3 AAA alkaline batteries in the transmitter and 4 AA alkaline batteries in the receiver.
Install the receiver and it's cover in the wall.
Switch the remote receiver to "remote" mode.
The remote control is ow ready for operation.

50 Ft.
32 Ft.
20 Ft.
12 Ft.
9 Ft.

Regency Horizon HZ54E Gas Fireplace

35

INSTALLATION
584 Proflame GT Series
Feature Sheet

1

1

1

(X) Indicates Included Feature

Note 1 ~ Proflame Flame Modulator for GTM & GTMF Remote Controls are sold seperately. Choice of NG or
LP flame modulator (to match unit fuel type). See Regency Retail Price pages for complete details
Note 2 ~ FPI Proflame Remote Controls come standard with white wall mount switch & cover plate.

36

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONBATTERY & ON | OFF SWITCH INSTALLATIONDFBC = digital fireplace burner control
1)

Remove glass door and valve cover (see valve cover removal
section in this manual) to access to DFBC & battery pack.

2)

Lift DFBC and battery pack up and out.

5) Locate the Green and White from the DFBC module wire harness;connect the spade connectors from the On/Off switch. Green to Blackand White to White.

6)

Reinstall the module and battery pack tray into the holder

3) Disconnect connector from battery holder and remove from tray –(battery holder is attached by Velcro to tray).

4) Install - 4 AA batteries, reconnect the connector to the battery pack andput back onto Velcro strip

Regency Horizon HZ54E Gas Fireplace

37

INSTALLATIONGT REMOTE INSTALLATIONDFBC = digital fireplace burner control
1)

Remove glass door to access to DFBC & battery pack tray.

2)

Lift DFBC and battery pack up and out.

6) Locate the DFC wire from the receiver wire harness and connect to theDC supply wire from the DFBC.

3) Disconnect connector from battery holder and remove from tray –(battery holder is attached by Velcro to tray).
Note: DO NOT USE 4 AA batteries in the battery pack on the tray - the
DFBC is now powered by the receiver batteries in the wall.

4) Remove the 4 AA batteries if installed, reconnect the connector to thebattery pack and put back onto Velcro strip
5) Locate the Green and White wires from the DFBC module wire harness;connect the spade connectors from the receiver wire harness, (TH)Green to (DFBC) Green and (TH/TP) White to (DFBC) White

38

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONGTM REMOTE INSTALLATIONDFBC = digital fireplace burner control
1)

Remove the faceplate and glass door to access to DFBC &battery pack tray.

2)

Lift DFBC and battery pack up and out.

3) Disconnect connector from battery holder and remove from tray –(battery holder is attached by Velcro to tray).

6) Locate the DFC wire from the receiver wire harness and connect to theDC supply wire from the DFBC.

Note: DO NOT USE 4 AA batteries in the battery pack on the tray - the
DFBC is now powered by the receiver batteries in the wall.

7) Remove the hi/lo knob from the valve head, if installed, by removing
2 screws as shown below.

4) Remove the 4 AA batteries if installed, reconnect the connector to thebattery pack and put back onto Velcro strip
5) Locate the Green and White wires from the DFBC module wire harness;connect the spade connectors from the receiver wire harness, (TH)Green to (DFBC) Green and (TH/TP) White to (DFBC) White

Regency Horizon HZ54E Gas Fireplace

8) Install the stepper motor in the same location the hi/lo knob wasremoved from - with 2 screws as shown below.

39

INSTALLATION
9) Install 4 - AA batteries into the receiver, ensure correct polarity.

10) Plug receiver wires into the back of the receiver and bundle wires
with the wire clip as shown below.

Wire Clip

11) Connect GTM motor wire from the stepper motor to the wire connector
from the receiver wire harness.

12) Program Receiver and transmitter (refer to manual)Note: DO NOT USE 4 AA batteries in the battery pack on the tray; theDFBC is now powered by the receiver batteries in the wall.

40

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONGTMF REMOTE INSTALLATIONDFBC = digital fireplace burner control
1)

Remove the faceplate and glass door to access to DFBC &battery pack tray.

2)

Lift DFBC and battery pack up and out.

6) Locate the DFC wire from the receiver wire harness and connect to th
DC supply wire from the DFBC. (insert pictures

3) Disconnect connector from battery holder and remove from tray – (battery
holder is attached by Velcro to tray).
7) Remove the hi/lo knob from the valve head, if installed, by removing
2 screws as shown below.

4) Remove the 4 AA batteries if installed, reconnect the connector to thebattery pack and put back onto Velcro strip

8) Install the stepper motor in the same location the hi/lo knob wasremoved from - with 2 screws as shown below.

5) Locate the Green and White wires from the DFBC module wire harness;connect the spade connectors from the receiver wire harness, (TH) Greento (DFBC) Green and (TH/TP) White to (DFBC) White

Regency Horizon HZ54E Gas Fireplace

41

INSTALLATION
9) Install 4 - AA batteries into the receiver.

12 Before installing the fan control module, install the heat shield on thecontrol module by securing with 2 screws.

13) From the wire harness, plug the FCM wire into the fan control modul

10) Plug ‘motor’ wires into the back of the receiver and bundle wires with thewire clip - as shown below.

FCM wire

Fan Control Module14) Install the fan control module onto the velcro pad located on the floor
the unit located left of the receiver.

11) Install the heat shield to the receiver with two screws and attach to thefloor of the unit with a velcro pad.

15) Plug fan control module into receptacle located on the left hand side ofunit.
16) Match the remote control to the receiver - see remote control
instructions.

Heat shield17) Reverse step 1.
18) Check to ensure there are no gas leaks..

42

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONOPTIONAL REFLECTIVE PANEL INSTALLATION
Before installation, panels must be handled and cleaned as per instructions noted below:

Stainless Steel Panels

Black Enamel Panels• Stainless panels must be inspected for scratches and dimples prior• Black Enamel panels must be inspected for scratches and dimples

to installation. All claims to be recorded at this time.
Claims for damage after installation will not receive consideration.

prior to installation. All claims to be recorded at this time.
Claims for damage after installation will not receive consideration.

• Use a hair dryer to remove the protective coating from the panels.
• To protect the finish during installation and handling - cotton gloves

MUST be worn at all times while handling the panels.

• Stainless panels will discolor a little during normal operation.

• Black Enamel panels will discolor a little during normal operation. This*All hand and finger marks MUST be cleaned off with a soft cloth. Usean ammonia based cleaner (ie. glass cleaner) to remove any fingerprints
before applying heat to the unit.
Failure to do this will result in burn stain on panels which you
will be unable to remove. Not protected by product warranty.

This is normal and should not be considered a defect.

All hand and finger marks MUST be cleaned off with a soft cloth anda stainless steel cleaner. Most stainless steel cleaners leave a film/
residue on the surface of the panels. Use an ammonia based cleaner(ie. glass cleaner) to remove this film before applying heat to the unit.
Failure to do this will result in burn stains on panels which you
will be unable to remove. Not protected by product warranty.

is normal and should not be considered a defect.

*1) Position the left side panel in place - top of panel in first, then fit thebottom tab into the slot at the bottom of the firebox as shown below.
Repeat for right side panel.
90 degree
bend faces
towards centerof unit on bothleft and rightside panels

Left Side
Panel
Shown

Right side panel in position
2) Fit the back panel into position by clearing the pilot shield - bottomof panel goes in first.
Then fit the tabs on the bottom left and right side of the back panel
into the slots at the base of the firebox.
Secure the back panel in place by placing the brackets over thescrews on the top of the inside left and right side of the firebox andtighten the screw to hold the bracket against the back panel shown
below.
Left Side
BracketFit side panel tab into slot

Right side back panel tab fitted into slot

Left side panel in position
Regency Horizon HZ54E Gas Fireplace

Bracket shown in place on right side of the firebox
43

INSTALLATIONGLASS CRYSTALS OR OPTIONAL CERAMIC STONESINSTALLATION ON BURNER
Evenly spread the supplied Glass Crystals or optional Ceramic Spa or Garden Stones over the burner. Ensure the crystals (or stones) do not
overlap too much as this will effect the flame pattern.
IMPORTANT NOTE:
Only the supplied approved Cobalt Glass, Ceramic Spa Stones or Garden Stones are to be used with these fireplaces. Use of any other type oglass crystals or stones can alter the unit's performance, any damage caused by the use of any unapproved glass or stones will not be covered
under warranty.
When using Ceramic or Garden Stones, DO NOT cover burner ports that lead to pilot flame. Ensure the crystals or stones do not overlap excessively
as this will effect the flame pattern.

Burner Packages
Unit

Glass Crystals

HZ54E / HZ54EPV

3 Bags1 Bag Glass + 2 packages (140 spa stones)

Ceramic Spa Stones

HZ42 / HZ42E

2 Bags1 Bag Glass + 1 package (70 spa stones)

HZ42 ST / HZ42STE
HZ42STEPV

2 Bags1 Bag Glass + 1 package (70 spa stones)

HZO42/HZO42 (AUS)

3 Bags

N/A

Garden Stones

1 package (50 stones)*HZ30E

1 bag

1 Bag Glass + 1 package (70 spa stones)

L676S

1 Bag

1 package = (70 spa stones)**P33S/P33SE

1 Bag

1 package = (70 spa stones)

U32S / U32SE

1 Bag

1 package = (70 spa stones)

E33S

1 Bag

1 package = (70 spa stones)

NOTE: 1 Ceramic spa stone package contains 70 stones
1 Garden stone package contains 50 stones*Recommended - use only 40 of the 70 ceramic stones on the HZ30E burner.
**Recommended - use only 50 of the 70 ceramic stones on the P33S/P33SE burner.

Glass Crystals shown on Burner
For Units HZ54E, HZ54EPV, HZ30E, HZ42ST, HZ42STE, HZ42E,
HZ42, HZO42 only

Glass Crystals shown on Burner
For units P33S,P33SE L676S, U32S, U32SE,E33S,only

Optional Ceramic Spa Stones + Glass Crystals shown on burner.
For Units HZ54E, HZ54EPV, HZ30E, HZ42ST, HZ42STE, HZ42,
HZ42E only

Optional Ceramic Spa Stones shown on burner.
For units P33S,P33SE L676S, U32S, U32SE, E33S only
Optional Garden Stones + Glass Crystals shown on burner.
For the HZO42 only

44

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONGLASS CRYSTALS OR OPTIONAL PEBBLESINSTALLATION ON FIREBOX BASE
Firebox Packages
Unit

Glass Crystals

Pebbles

HZ54E / HZ54EPV

6 Bags2 packages (6 x bags pebbles)

HZ42 / HZ42E

5 Bags2 packages (6 x bags pebbles)

HZ42 ST / HZ42STE

5 Bags2 package (6 x bags pebbles)

HZO42 / HZO42 (AUS)

3 Bags1 package (3 x bags pebbles)

HZ30E

2 bags1 package (3 x bags pebbles)

P33S/P33SE

3 Bags1 package (3 x bags pebbles)

U32S/U32SE

3 Bags1 package (3 x bags pebbles)

E33S

3 Bags1 package (3 x bags pebbles)

There are 3 optional packages to choose from to cover the firebox base:1) White River Pebbles2) Natural River Pebbles
3) Glass Crystals (4 colors available)
Spread the pebbles / crystals evenly on the exposed base of the firebox. Pebbles are NOT to be placed anywhere on the burner or over top of the
Glass Crystals or optional Ceramic Spa Stones.
NOTE: Only the supplied and approved pebbles / crystals are to be used.
Use of any other type of pebbles or material can create a danger and will void warranty.

White River Pebbles shown surrounding the Burner

Natural River Pebbles shown surrounding the BurnerWhite River Pebbles shown surrounding the Burner

Glass Crystals shown surrounding the Burner

Regency Horizon HZ54E Gas Fireplace

45

INSTALLATIONOPTIONAL LOG SET INSTALLATION
Installation of Reflective Panels must be completed before installing the log set.
Read the instructions below carefully and refer to the images. If thelogs are broken do not use the unit until they are replaced.
Broken logs can interfere with pilot operation.
Improper positioning of the logs may create carbon build-up and canalter the unit's performance which is not covered under warranty.
Log kit # 476-930 contains the following pieces:
Part #
Ax2
Bx2
Cx2
Dx2
476-103 x 12
946-669

C

Description
Log
Log
Log
Log
Pin Clips
Platinum Embers

C

D

D

B
A
A

B

1) Remove the following if already installed:a) Faceplateb) Glass Doorc) Pebblesd) Glass Crystalse) Stones

Diagram 1

Note: Aeration Setting is set at 1/2" from the factory. The following are recommended settings for NG and LP units when using the log set :NG = 1/2"
LP = Full Open
2) Attach the 12 pin clips to the bottom cover (not the burner) in the exact locations indicated by an X, as shown in Diagram 2 below.
All measurements along the front
and back edge originate from centre
line.
Centerline indicated by "V" cut out
on the rear edge of the burner.

Note: Front and back measurements originate from the centre line of burner.
Side measurements originate from front edge of the bottom cover (see Diagram 3).
Note: Units may have dimples on the burner to indicate pin clip installation points.
If dimples are not present on the burner, follow the above directions.

19-3/16”

19-3/16”

15-3/4”

7-3/4”

4-3/4”

6”

x

x

x

x

1-1/2”xx

19”8-3/4”

Back

x

x

x

5-5/8”

v
CL

17”

Front

x

x

x

7-1/2”

11-3/8”

19-1/2”

20-5/8”20-5/8”3) Pin clips are attached to the lip edge of the bottom cover (not the burner) see diagrams 3 & 4.

2”

Diagram 2
Measurements tocentre of pins.

Burner

Lip Edge

Bottom CoverSide measurementsfrom corner edge.

Di
46

4

Regency Horizon HZ54E Gas Fireplace

INSTALLATION

Diagram 5
Pin clips installed - dots indicate dimple locations.
*Actual dimples/pin clips are black - not white as shown4) Install the glass crystals (see glass crystal installation section in this manual).

Diagram 65) Place platinum embers on glass crystals as shown in diagram 7.

Diagram 76) If installing optional pebbles - install pebbles before log installation.

Diagram 8

Regency Horizon HZ54E Gas Fireplace

47

INSTALLATION
7) Place logs A + B on the burner, rest logs on the pin clips, as shown in diagram 9.
Note: Logs should be oriented exactly as shown in diagram 9.

A

B

A

B

Diagram 98) Place logs C + D on logs A + B, as shown in diagram 10.
Note: Logs should be oriented exactly as shown in diagram 10.

D
D

C

C

Diagram 10
9) Install the following:a) *Glass doorb) *Faceplate and door frame*Refer to these sections in the manual for detailed instructions.

Log Set Installed (shown with optional pebbles)48

Diagram 11

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONFACEPLATE &DOOR FRAME OVERLAY INSTALLATION
1) Install the door frame overlay by hooking the top flange over top of
the glass door, push in the bottom of the door frame overlay to securein place.

3) Secure the left side mounting bracket to the backside of the faceplate
as shown below. Use 3 screws supplied to secure the mounting
bracket in place. Repeat for right side.

Glass Door

Door Frame
Overlay

Left Side
Mounting Bracket

Mounting Bracket
shown in place

NOTE: Ensure that the faceplate is positioned correctly when installingthe mounting brackets to the faceplate. There is a top and bottom,
the top of the faceplate has 4 tabs whereas the bottom only has 2
as shown in the diagram below.

Magnet Position
2) Place 2 of the supplied magnets on the lower corners of the Door
Frame Overlay, this will keep the Faceplate in postion after it has
been installed.

Regency Horizon HZ54E Gas Fireplace49

INSTALLATION
4) Install the faceplate to the unit by hooking the left and right side
mounting brackets into the mounting slots at the side of the firebox
as shown below. It is recommended that you use the first mounting
slot (the one closest to the door frame overlay) out of the 5 so thatthe faceplate and door frame overlay are flush with one another. See
diagram below.
NOTE: There are 5 mounting slots available, this is to accomodate
any finishing that protrudes slightly beyond the faceplate.

IMPORTANT NOTE
To ensure the gap between the door frame and the faceplate
are equal from side to side you may need to slide the faceplateslightly to the left or right accordingly.
Also if necessary, the faceplate may be adjusted up and down
by loosening the top screw as shown in the diagram below andsliding the plate up or down as required.

Faceplate Mounting Slots
First Mounting Slot(recommended)

Completed Faceplate & Door Frame Overlay Installation

50

Regency Horizon HZ54E Gas Fireplace

INSTALLATIONOPTIONAL FAN INSTALLATION
Important: 120 Volt AC power is needed for the fan switch and blower.
The receptacle box will be installed on the left hand side of the unit
and must be wired by a qualified electrician prior to fan
assembly being installed. The neutral(wider) slot of the polarized
receptacle should be at the top.

5) Remove the glass door.
a) Remove cover plates from over each screw by pulling away frommagnets each as shown below.

1) Turn the unit off and allow it to cool down to room temperature.
2) Turn off the gas supply to the unit.
3) Remove the faceplate by lifting it up off the hinges on the sides of thefirebox.

MagnetCover Plate

Diagram 4b) Remove the 3 screws shown below at the bottom of the glass
door.
c) Swing the door out 45o from the bottom and lift up and out.

4) Remove the door frame overlay by swinging out 45o from the bottom andlift up and out.

Steps 6 & 7 for NG units only:
6) Remove the burner tray by undoing the 2 screws in between thebottom cover and burner on the firebox. Carefully lift the burner up andout ensuring not to spill the glass crystals.

Aerial View of the inside of the unit shown.
7) Remove bottom cover by undoing 3 screws securing it to the firebox
base, lift up and out.

Regency Horizon HZ54E Gas Fireplace

51

INSTALLATION
Steps 8 & 9 for NG unit only:
8) Loosen 6 screws that secure the burner extenders. on burner tray,
located behind the burner on either side of the pilot assembly.

13) Manoeuvre the fan into position on the floor of the unit. Tilt the fan
to get through the fan access panel and into position.

9) Lift out the 2 burner tray extenders.

Burner tray extenders

14) Secure the fan to the floor of the unit with 2 screws.
*See wiring diagram in manual.

Burner tray

Burner tray extenders
10) After extenders have been removed. Remove the 2 screws that
secure the burner tray, at the base of the firebox.
11) Slide the burner to the left and lift it out.

15) Attach the ground wire from the fan to the ground lug in the unit. The
ground lug is located just in front of the receptacle box on the left
side on the floor of the unit. Plug fan
If installing a GTMF system - go to step 20 before proceeding.

Location of screws securing burner12) Remove 8 screws to remove the fan access panel cover - located on
the left hand side floor of the firebox.

Ground Lug16) Slide the thermodisc into the bracket on the bottom side of the fanaccess panel - check fan access panel gasket - replace if necessary.

Fan Access Panel

52

Regency Horizon HZ54E Gas Fireplace

INSTALLATION
17) Reverse Steps 8 through 5.
18) Install the fan air deflector - it hooks to 2 brackets on to the bottom lip of
the unit, to the right of the receiver.

21) Attach the receiver to the unit with the velcro strip. Place the receiverin front of the ground lug on the left side of the unit - inside the bottom
frame of the unit - follow steps 15-19 to complete installation.

Air deflector

BracketTO REMOVE THE FAN
1) Turn the power off.
2) Reverse the above instructions.
Maintenance: The sealed bearings are lubricated, there is no need to lubricate them further. (Extra lubricant will cause more lint and dust buildup- causing the bearings to prematurely fail).
Regular cleaning and vacuuming of the fan area will add to the life of the
motor.

Air deflector

19) Reverse Steps 4 through 1.
20) FOR GTMF INSTALLATIONS ONLY: Install the fan control module into
the unit through the open fan access panel. Plug the fan control module
into the receptacle in the unit (left side - floor of unit). Plug the fan into
the fan control module and connect GTMF remote (see GTMF installation
instructions in this manual).

IMPORTANT:
These fans collect a lot of dust from within your home. Ensure you
maintain these fan motors on a regular basis by vacuuming
the fan blades and housing using a soft brush nozzle.

FAN
10”

6-1/2”
7”

FCM
RECEIVER

Top View

Regency Horizon HZ54E Gas Fireplace53

OPERATING INSTRUCTIONSOPERATING
INSTRUCTIONSLIGHTING
PROCEDURE

1) Read and understand these instructions
before operating this appliance.

IMPORTANT
To ignite or reignite the pilot, youmust first remove the glass door.

2) Check to see that all wiring is correct andenclosed to prevent possible shock.
3) Check to ensure there are no gas leaks.

1) Press and release on ON/OFF button once
on the remote control or ON/OFF switch.

4) Make sure the glass in the glass door frame
is properly positioned. Never operate theappliance with the glass removed.

2) After approximately 4 seconds the spark
ignition system will spark for 60 seconds tolight the main burner.

5) Verify that the venting and cap areunobstructed.

3) The unit will turn on.

6) The unit should never be turned off, and on
again without a minimum of a 60 second
wait.

FIRST FIRE
The FIRST FIRE in your heater is part of thepaint curing process. To ensure the paint isproperly cured, it is recommended you burnyour fireplace for at least four (4) hours the firsttime with the fan on.
When first operated, the unit will release anodour caused by the curing of the paint and theburning off of any oils remaining from manufacturing. Smoke detectors in the house may go off
at this time. Open a few windows to ventilate
the room for a couple of hours. The glass may
require cleaning.
NOTE: When the glass is cold and the applianceis lit, it may cause condensation and fog
the glass. This condensation is normal
and will disappear in a few minutes as
the glass heats up.

DO NOT ATTEMPT TO CLEAN THE
GLASS WHILE IT IS STILL HOT!
DO NOT BURN THE UNIT WITHOUT THE
GLASS DOOR IN PLACE.

Note: The first try for ignition will last approximately 60 seconds. If there is no flame ignition(rectification) the board will stop sparking for
approximately 35 seconds. After wait time
, the board will start second try for ignitionby sparking for approximately 60 seconds .
If there is still no positive ignition the board
will go into lock out.
The system will need to be reset as follows:a) Turn the system off using ON/OFF switch
or press ON/OFF button - if using optional
remote.
b) After approximately 2 seconds turn on ON/
OFF switch or press ON/OFF button if using
optional remote.
c) Repeat step 2.

SHUTDOWNPROCEDURENORMAL OPERATINGSOUNDS OFGAS APPLIANCES
It is possible that you will hear some sounds fromyour gas appliance. This is perfectly normal due tothe fact that there are various gauges and typesof steel used within your appliance. Listed below
are some examples. All are normal operating
sounds and should not be considered as defects
in your appliance.
Burner Tray:
The burner tray is positioned directly under theburner and is made of a different gauge material
from the rest of the firebox and body. Therefore,
the varying thicknesses of steel will expand andcontract at slightly different rates which can cause"ticking" and "cracking" sounds. You should also
be aware that as there are temperature changes
within the unit these sounds will likely re-occur.
Again, this is normal for steel fireboxes.
Pilot Flame:
While the pilot flame is on it can make a veryslight "whisper" sound.
Gas Control Valve:
As the gas control valve turns ON and OFF, adull clicking sound may be audible, this is normal
operation of a gas regulator or valve.
Unit Body/Firebox:
Different types and thicknesses of steel will
expand and contract at different rates resulting
in some "cracking" and "ticking" sounds will beheard throughout the cycling process.
Blower Thermodisc:
When this thermally activated switch turns ON
it will create a small "clicking" sound. This is theswitch contacts closing and is normal.

1) Turn the wall mounted switch or remote to
the "OFF" position.
2) Press "OFF" on the remote control.
3) Turn the gas control knob to the "OFF" position to turn off the pilot.

During the first few fires, a white film
may develop on the glass front as part ofthe curing process. The glass should becleaned after the unit has cooled downor the film will bake on and become very
difficult to remove. Use a non-abrasive
cleaner and DO NOT ATTEMPT TO CLEAN
THE GLASS WHILE IT IS HOT.

54

Regency Horizon HZ54E Gas Fireplace

OPERATING INSTRUCTIONSINSTALLATIONCOPY OF LIGHTING PLATE INSTRUCTIONSFOR YOUR SAFETY READ BEFORE LIGHTINGThis appliance must be installed in accordance with local codes, if any;
if none, follow the National Fuel Gas Code, ANSI Z223.1/NFPA 54, orNatural Gas and Propane Installation Codes, CSA B149.1.

WARNING: If you do not follow these instructions exactly, a fire or explosion may result
causing property damage, personal injury or loss of life. Improper installation, adjustment,
alteration, service or maintenance can cause injury or property damage. Refer to the owner’s
information manual provided with this appliance. For assistance or additional information
consult a qualified installer, service agency or gas supplier.
AVERTISSEMENT. Quiconque ne respecte pas à la lettre les instructions dans la présente noticerisquede déclencher un incendie ou une explosion entraînant des dommages, des blessures ou
la mort.
Une installation, d'ajustement, de modification, de service ou d'entretien peut provoquer
des blessures ou des dommages matériels. Reportez-vous au manuel du propriétaire del'information fournie avec cet appareil. Pour obtenir de l'aide ou des informations supplémentaires consulter un installateur qualifié, une agence de service ou fournisseur de gaz.
A) This appliance is equipped with an ignition device which automatically lights the pilot.
Do not try to light the pilot by hand.
B) BEFORE OPERATING smell all around the appliance area for gas. Be sure to smell next to the floor
because some gas is heavier than air and will settle on the floor.
WHAT TO DO IF YOU SMELL GAS- Do not try to light any appliance.
- Do not touch any electric switch, do not use any phone in your building.
- Immediately call your gas supplier from a neighbours phone. Follow the gas supplier’s instructions.
- If you cannot reach your gas supplier, call the fire department.
C) Do not use this appliance if any part has been under water. Immediately call a qualified service
technician to inspect the appliance and replace any part of the control system and any
gas control which has been underwater.
A) Cet appareil est muni d’un dispositif d’allumage qui allume automatiquement la veilleuse.
Ne tentez pas d’allumer la veilleuse manuellement.
B) AVANT DE FAIRE FONCTIONNER, reniflez tout autour de l’appareil pour déceler une odeurde gaz. Reniflez près du plancher, car certains gaz sont pluslourds que l’air et peuvent
s’accumuler au niveau du sol.
QUE FAIRE SI VOUS SENTEZ UNE ODEUR DE GAZ :• Ne pas tenter d’allumer d’appareil• Ne touchez à aucun interrupteur; ne pas vous servir des téléphones se trouvant dans lebâtiment.
• Appelez immédiatement votre fournisseur de gaz depuis un voisin. Suivez les
instructions du fournisseur.
• Si vous ne pouvez rejoindre le fournisseur, appelez le service des incendies
C) N’utilisez pas cet appareil s’il a été plongé dansl’eau, même partiellement. Faites inspecter l’appareil par un technicien qualifié et remplacez toute partie du système de contrôle et toute commande qui ont été plongés dans l’eau.

CAUTION: Hot while in operation. Do not touch. Severe Burns may result. Due to high surface
temperatures keep children, clothing and furniture, gasoline and other liquids having flammablevapors away. Keep burner and control compartment clean. See installation and operating
instructions accompanying appliance.

LIGHTING INSTRUCTIONS
1) Turn on ON/OFF switch
2) After approximately 4 seconds the spark ignition system will spark for 60 seconds to light the mainburner.
3) The unit will turn on.
Note: The first attempt to ignition will last approximately 60 seconds. If there is no flame ignition (rectification) the board will stop sparking for approximately 35 seconds. After this wait time, the board will start a
second try for ignition by sparking for approximately 60 seconds. If there is still no positive ignition after thesecond attempt the board will go into lock out.
The system will need to be reset as follows (after going into lock out mode):a) Wait 5 minutes - turn the system off using ON/OFF switch.
b) After approximately 2 seconds turn on ON/OFF switch or press ON/OFF button if using optional
remote.
c) Unit will repeat step 2.
1) Appuyez le bouton ON / OFF
2) Attendre 4 secondes. Le système d’allumage produira des étincelles pendant 60 secondes afin d’amorcer
le brûleur principal.
3) Les flammes s’allumeront.
Remarque : Au premier allumage, le système tente d’allumer les flammes pendant 60 secondes. Si l’essai est
infructueux, le système fait une pause de 35 secondes. C’est ce qu'on appelle l'étape de rectification. Ce délaiécoulé, le système tente à nouveau d'allumer les flammes en produisant des étincelles pendant 60 secondes.
Si les flammes ne s’allument toujours pas, le système se met en mode verrouillage.
Il faut alors le réinitialiser en suivant les étapes ci-dessous (pour le déverrouiller) :a) Attendre 5 minutes et éteindre l’appareil en réglant l’interrupteur à la position « OFF »;b) Attendre 2 secondes et rallumer le système à l’aide de l’interrupteur ou de la télécommande.
c) L'unité répétera l'étape 2.

TO TURN OFF GAS APPLIANCE
1)
2)

Turn off ON/OFF switch
If service is to be performed - you must disconnect power to the unit, from the battery pack, refer tomanual.

1)
2)

Appuyez sur le bouton ON / OFF
Si le service est effectuée, vous devez débrancher l'appareil, du bloc-piles, voir le manuel d'instruction
pour plus de détails.

DO NOT REMOVE THIS INSTRUCTION PLATE

Regency Horizon HZ54E Gas Fireplace918-628b55

MAINTENANCE
MAINTENANCE
INSTRUCTIONSGENERAL VENTMAINTENANCE

1) Always turn off the gas valve before cleaning.
For relighting, refer to lighting instructions. Keep
the burner and control compartment clean bybrushing and vacuuming at least once a year.

Conduct an inspection of the venting system semiannually. Recommended areas to inspect as follows:2) Clean appliance and door with a damp cloth(never when unit is hot). Never use an abrasive
cleaner. The glass should be cleaned with agas fireplace glass cleaner. The glass should
be cleaned when it starts looking cloudy.
3) The faceplate is finished in a heat resistantpaint and should only be refinished with heat
resistant paint. Regency® uses StoveBright
Paint - Metallic Black #6309.
Note: Faceplates and inner panels made fromstainless steel will naturally change
color over time.

1) Check the Venting System for corrosion in areasthat are exposed to the elements. These willappear as rust spots or streaks, and in extreme
cases, holes. These components should be
replaced immediately.
2) Remove the Cap, and shine a flashlight down the
Vent. Remove any bird nests, or other foreignmaterial.
3) Check for evidences of excessive condensation,such as water droplets forming in the inner
liner, and subsequently dripping out the joints,
Continuous condensation can cause corrosionof caps, pipe, and fittings. It may be causedby having excessive lateral runs, too many
elbows, and exterior portions of the systembeing exposed to cold weather.

4) Make a periodic check of burner for proper
position and condition. Visually check theflame of the burner periodically, making surethe flames are steady; not lifting or floating.
If there is a problem, call a qualified service
person.

4) Inspect joints, to verify that no pipe sections or
fittings have been disturbed, and consequently
loosened. Also check mechanical supports suchas Wall Straps, or plumbers' tape for rigidity.

5) The appliance and venting system must be
inspected before use, and at least annually,
by a qualified field service person, to ensurethat the flow of combustion and ventilation air
is not obstructed.

GLASS GASKET

Note: Never operate the appliance without theglass properly secured in place.
6) Do not use this appliance if any part has been
under water. Immediately call a qualified service
technician to inspect the appliance and to
replace any part of the control system and any
gas control which has been under water.
7) In the event this appliance has been serviced
check that the vent-air system has been properly
resealed & reinstalled in accordance with the
manufacturer's instructions.

GLASS DOORYour Regency® fireplace is supplied with hightemperature 5mm-Ceramic glass. If your glass
requires cleaning, we recommend using anapproved glass cleaner available at all authorized
dealers. Do not use abrasive materials.

CAUTION & WARNINGS:* Do not clean when the glass is hot.
* The use of substitute glass will void all productwarranties.
* Care must be taken to avoid breakage of theglass.
* Do not strike or abuse the glass.
* Do not operate this fireplace without the glass
front or with a cracked or broken glass front.
* Wear gloves when removing damaged or broken
glass.
* Replacement of the glass panel(s) should bedone by a licensed or qualified service per son.

GLASS REPLACEMENT
In the event that you break your glass by impact,
purchase your replacement from an authorized
Regency® dealer only.
Replacement glass is shipped already installed
into the door frame.

If the glass gasket requires replacement use atadpole glass gasket (Part # 936-159).

CAUTION: Wear gloves whenremoving damaged or broken glass.

WARNING: Do not operate theappliance with the glass panels
removed, cracked or broken.
Replacement of the glass panels
should be done by a licensed or
qualified service person.

8) Verify operation after servicing.

56

Regency Horizon HZ54E Gas Fireplace

MAINTENANCEGLASS DOOR REMOVAL
1) Turn the unit off and allow it to cool down to room temperature.
2) Turn off the gas supply to the unit.

5) Remove the glass door.
a) Remove cover plates from over each screw by pulling away from 2
magnets each as shown below.

3) Remove the faceplate by lifting it up off the hinges on the sides of thefirebox.

MagnetCover Plate

Diagram 4b) Remove the 3 screws shown below at the bottom of the glass
door.
c) Swing the door out 45o from the bottom and lift up and out.

4) Remove the door frame overlay by swinging out 45o from the bottom
and lift up and out.

6) Remove valve cover - (see valve cover removal section in this manual).

Regency Horizon HZ54E Gas Fireplace

57

MAINTENANCEVALVE TRAY REPLACEMENT
1) Turn the unit off and allow it to cool down to room temperature.
2) Turn off the gas supply to the unit.
3) Remove the faceplate by lifting it up off the hinges on the sides of thefirebox.

5) Remove the glass door.
a) Remove the 3 screws shown below at the bottom of the glass
door.
b) Swing the door out 45o from the bottom and lift up and out.

Note: See next pages for specific instructions for NG / LP units.
4) Remove the door frame overlay by swinging out 45o from the bottom
and lift up and out.

58

Prior to removing burner - remove the following (if installed):-crystals-pebbles-spa stones-logs-Inner panels

Regency Horizon HZ54E Gas Fireplace

MAINTENANCE
HZ54E-NG UNIT
1) Remove the burner tray by undoing the 2 screws in between the bottom cover and burner on the firebox. Carefully lift the burner up andout ensuring not to spill the glass crystals.

5) Lift out the DFBC and battery pack.

Aerial View of the inside of the unit shown.
2) Remove bottom cover by undoing 3 screws securing it to the firebox
base, lift up and out.

DFBC

Battery pack6) Disconnect the CN4 and CN3 wires from the DFBC.
CN4

CN3

7) Remove the valve tray by undoing 12 screws.

Aerial View of the inside of the unit shown.

3) Disconnect the green and orange wires from the valve.

8) Partially lift out valve tray.
9) Disconnect the inlet gas line.
Green Wire

Orange Wire

4) Disconnect the green ground wire from the valve bracket.

Green ground wire

Regency Horizon HZ54E Gas Fireplace

10) Replace valve and reverse steps.
59MAINTENANCE
HZ54E-LP UNIT
1) Loosen 6 screws that secure the burner extenders. on burner tray,
located behind the burner on either side of the pilot assembly.

7) Disconnect the green and orange wires from the valve.

2) Lift out the 2 burner tray extenders.

Burner tray extenders

Green Wire

Orange Wire

Burner tray
8) Disconnect the green ground wire from the valve bracket.

Burner tray extenders4) After extenders have been removed. Remove the 2 screws that
secure the burner tray, at the base of the firebox.
5) Slide the burner to the left and lift it out.

Green ground wire9) Remove the valve tray by undoing 12 screws.

Location of screws securing burner10) Partially lift out valve tray.
11) Disconnect the inlet gas line.

Burner Bracket6) With burner removed - lift out burner tray.

Gas Inlet Line
12) Replace valve and reverse steps.

60

Regency Horizon HZ54E Gas Fireplace

PARTS LIST
MAIN ASSEMBLY
Part #

Description

Part #

1) 476-151
476-1522) 476-525
476-530
3) 476-574E/P
476-576E/P

Bottom Cover (False Tray) NG
Bottom Cover (False Tray) LP
Burner Assembly -NG
Burner Assembly-LP
Valve Assembly -NG
Valve Assembly-LP6) 904-660
904-431904-658
7) 476-101
476-042f
8) 476-915

4) 911-004
911-005
5) 911-006
911-007886 SIT Valve - NG
886 SIT Valve - LP
Pilot Assembly - NG
Pilot Assembly - LP

370-055
476-023476-055
521-035

Flue Collar Gasket
Plate Relief Gasket
Valve Tray Gasket
Inner Flue Collar Gasket

White Wall Switch
White Switch Plate Wire

940-359/P
476-011

Flush Glass
Flush Door

911-019948-409476-080
946-556946-570

Wire (Valve to Burner ON/OFF)
Flue Collar
Lifting Handle
Heatwave Kit
Heatrelease Kit

918-883

Manual

910-363910-366

Description
Burner Orifice # 30 (NG)
Burner Orifice # 49 (LP)
Inlet Gas Flex Line SS
Burner Extenders (LP unit only)
LH / RH Nailing Strips
Optional Fan

HEAT WAVE DUCT KIT

7

5
1

6

8

2
3
4

HEAT RELEASE DUCT KITRegency Horizon HZ54E Gas Fireplace

61

PARTS LISTACCESSORIESPart #

Description30) 476-907
476-908

Reflective Stainless Steel Panels
Black Enamel Inner Panels

31) 476-924
476-927476-926

Faceplate & Door Frame Overlay - Black
Faceplate & Door Frame Overlay - Stainless Steel
Faceplate & Door Frame Overlay - Sunset Bronze

946-671946-672946-673946-674476-930

Cobalt Blue Glass Crystals
Natural River Pebbles
White River Pebbles
StonesLog Set946-690946-691946-692

GT remote
GTM remote
GTMF remote

910-576910-572

Cover Wall Mount
Receiver GTM SIT w/Batt & Cover

30

31

62

Regency Horizon HZ54E Gas Fireplace

WARRANTY

Regency® Fireplace Products are designed with reliability and simplicity in mind. In addition, our internal Quality Assurance Team carefully inspects each unit thoroughly
before it leaves our facility. Regency Fireplace Products is pleased to extend this limited lifetime warranty to the original purchaser of a Regency® Product. This warranty is
not transferable.
The Warranty: Limited Lifetime
The combustion chamber, heat exchanger, burner tubes/pans, logs, glass crystals, ceramic spa stones, pebbles, brick panels and gold plating (against defective manufacture only) arecovered under the Limited Lifetime Warranty for five (5) years for parts and subsidized labour* and parts only thereafter.
Glass is covered for lifetime against thermal breakage only, parts and subsidized labour* for five (5) years and parts only thereafter from date of purchase.
External casting, surrounds and grills are covered against cracks and warps resulting from manufacturer defects, parts and subsidized labour* for three (3) years from the date of purchaseand parts only thereafter.
Special Finishes - One year on stainless steel panels, nickel overlays,nickel faceplates, brushed nickel and antique copper full screens and doors. You can expect some changes in color
as the product "ages" with constant heating and cooling. FPI warranties the product for any manufacturing defects on the original product. However, the manufacturers warranty does notcover changing colors and marks, ie. finger prints, etc applied after the purchase of the product. Damage from the use of abrasive cleaners is not covered by warranty.
Electrical and mechanical components such as blowers, switches, wiring, thermodiscs, FPI remote controls, spill switches, thermopiles, thermocouples, pilot assembly components, andgas valves are covered for two years parts and one year subsidized labour* from the date of purchase. Blowers and valves replaced under warranty are considered repairs and continue
as if new with appliance. ie. twelve (12) months from original purchase date of appliance with a minimum of three (3) months coverage from date of replacement.
FPI venting components are covered parts and subsidized labour* for three (3) years from date of purchase.
Simpson Dura-Vent venting components (Direct Vent units) are covered by Simpson Dura-Vent Inc. warranty.
Repair/replacement parts purchased by the consumer from FPI after the original coverage has expired on the unit will carry a 90 day warranty, valid with a receipt only. Any item shown to
be defective will be repaired or replaced at our discretion. No labor coverage is included with these parts.
Conditions:
Any part or parts of this unit which in our judgement show evidence of such defects will be repaired or replaced at FPI's option, through an accredited distributor or agent provided that thedefective part be returned to the distributor or agent Transportation Prepaid, if requested.
Porcelain/Enamel - Absolute perfection is either guaranteed nor commercially possible. Any chips must be reported and inspected by an authorized dealer within three days of installation.
Reported damage after this time will be subject to rejection.
It is the general practice of FPI to charge for larger, higher priced replacement parts and issue credit once the replaced component has been returned to FPI and evaluated for manufacturer
defect.
The authorized selling dealer is responsible for all in-field service work carried out on your Regency® product. FPI will not be liable for results or costs of workmanship from unauthorized
service persons or dealers.
At all times FPI reserves the right to inspect product in the field which is claimed to be defective.
All claims must be submitted to FPI by authorized selling dealers. It is essential that all submitted claims provide all of the necessary information including customer name, purchase date,serial #, type of unit, problem, and part or parts requested, without this information the warranty will be invalid.
Exclusions:This limited Lifetime Warranty does not extend to or include paint, door or glass gasketing or trim.
At no time will FPI be liable for any consequential damages which exceed the purchase price of the unit. FPI has no obligation to enhance or modify any unit once manufactured. ie. as
products evolve, field modifications or upgrades will not be performed.
FPI will not be liable for travel costs for service work.
Installation and environmental problems are not the responsibility of the manufacturer and therefore are not covered under the terms of this warranty policy.
Embers, rockwool, gaskets, door handles and paint are not covered under the terms of this warranty policy.
Any unit which shows signs of neglect or misuse is not covered under the terms of this warranty policy.
The warranty will not extend to any part which has been tampered with or altered in any way, or in our judgment has been subject to misuse, improper installation, negligence or accident,
spillage or downdrafts caused by environmental or geographical conditions, inadequate ventilation, excessive offsets, negative air pressure caused by mechanical systems such as
furnaces, fans, clothes dryer, etc.
Freight damage to stoves and replacement parts is not covered by warranty and is subject to a claim against the freight carrier by the dealer.
FPI will not be liable for acts of God, or acts of terrorism, which cause malfunction of the appliance.
Performance problems due to operator error will not be covered by this warranty policy.
Products made or provided by other manufacturers and used in conjunction with the operation of this appliance without prior authorization from FPI, may nullify your warranty on this product.
Any alteration to the unit which causes sooting or carboning that results in damage to the interior / exterior facia is not the responsibility of FPI.
* Subsidy according to job scale as predetermined by FPI.

Regency Horizon HZ54E Gas Fireplace

63

Register your Regency® warranty online

www.regency-fire.com
Reasons to register your product online today!
• View and modify a list of all your registered products.
• Request automatic email notification of new product updates.
• Stay informed about the current promotions, events, and special
offers on related products.

Installer: Please complete the following information
Dealer Name & Address: _________________________________________________________________________________________________________________
Installer: ___________________________________________________________
Phone #: ___________________________________________________________
Date Installed: ______________________________________________________
Serial No.: __________________________________________________________

Regency Horizon and SureFire™ are trademarks of FPI Fireplace Products International Ltd.
© Copyright 2010, FPI Fireplace Products International Ltd. All rights reserved.

Printed in Canada