Jøtul GF 370 DV
Direct Vent Gas Stove

Installation andOperation Instructions
WARNING: If the information in these
instructions is not followed exactly, a fireor explosion may result causing property
damage, personal injury or loss of life.
– Do not store or use gasoline or otherflammable vapors and liquids in the vicinityof this or any other appliance.
– WHAT TO DO IF YOU SMELL GAS

ATTENTION : CES INSTRUCTIONS DOIVENTDEMUERER AVEC LE PROPRIÉTERE D’UNE
MAISON.
AVERTISSEMENT: Assurez-vous de bien suivreles instructions données dans cette noticepour réduire auninimum le risque d’incendie
ou d’explosion ou pour éviter tout dommage
matériel, toute blessure ou la mort.

• Do not try to light any appliance.

– Ne pas entreposer ni utiliser d’essence ni
d’autres vapeurs ou liquides inflammables
dans le voisinage de cet appareil ou de tout
autre appareil.

• Immediately call your gas supplier from aneighbor’s phone. Follow the gas supplier’s
instructions.

– QUE FAIRE SI VOUS SENTEZ UNE ODEUR DE
GAZ:• Do not touch any electrical switch; do not
use any phone in your building.

• If you cannot reach your gas supplier, callthe fire department.

– Installation and service must be performed
by a qualified installer, service agency or thegas supplier.
– In the Commonwealth of Massachusetts,
a carbon monoxide (CO) detector shall be
installed in the same room as the appliance.

This appliance may be installed in an aftermarket,
permanently located, manufactured home or mobile
home, where not prohibited by local codes.
This appliance is only for use with the types of gas
indicated on the rating plate. A conversion kit issupplied with the appliance.

• Ne pas tenter d’allumer l’appareil.

• Ne touchez à aucum interrupteur. Ne
pas vous servir des téléphones se trouvant dans le bâtiment où vous trouvez.

• Appelez immédiatement votre fournisseur de gaz depuis un voisin. Suivez les
instructions du fournisseur.

• Si vou ne pouvez rejoindre le fournisseur de gaz, appelez le service des incendies.

– L’installatione l’entretien doivent êtreassurés par un installateur ou un service
d’entretien qualifié ou par le fournisseurde gaz.

INSTALLER: Leave this manual with the appliance.

CONSUMER: Retain this manual for future reference.

138914 Rev. K / 7.27.10




THIS OWNER’S MANUAL PROVIDES INFORMATION TO
ENSURE SAFE INSTALLATION AND EFFICIENT, DEPENDABLEOPERATION OF YOUR FIREPLACE INSERT. PLEASE READ
THESE INSTRUCTIONS IN THEIR ENTIRETY AND MAKE THEMAVAILABLE TO ANYONE USING OR SERVICING THIS GASINSERT.
DO NOT ATTEMPT TO ALTER OR MODIFY THE CONSTRUCTION
OF THIS APPLIANCE OR ITS COMPONENTS. ANY
MODIFICATION OR ALTERATION WILL VOID THE WARRANTY,CERTIFICATION AND LISTING OF THIS APPLIANCE.

Your fireplace insert has a unique serial number
stamped on the rating plate which is located in the valve
compartment. Please record the serial number in thespace below. You may also wish to attach your purchasereceipt to this page for future reference.
MODEL NAME: Jøtul GI 450 DV II Katahdin Gas Fireplace
SERIAL NUMBER:_______________________________DATE OF PURCHASE:____________________________AUTHORIZED DEALER:__________________________ADDRESS ___________________________________
PHONE: ____________________________________THIS PRODUCT MUST BE INSTALLED BY
A LICENSED MASTER OR JOURNEYMANPLUMBER OR GAS-FITTER WHEN
INSTALLED IN THE COMMONWEALTH OFMASSACHUSETTS.

Suggested Tools for
Installation and Service• External regulator (for Propane only)• Piping which complies with local code
• Manual shut-off valve T-Handle required in Massachusetts• Sediment trap - if required by code
• Tee joint• Pipe wrench• Pipe sealant• 10 mm open end wrench• 1/2”, 7/16” open end wrench• Phillips head screwdriver• Flat head screwdriver• 1/4” nut driver• Gloves• Safety glasses• Torx T-20 screwdriverWe� recommend thatour gas products beinstalled and serviced byprofessionals who are
certified in the U.S. by
the National Fireplace
Institute® (NFI) as NFI Gas
Specialists.

INSTALLER:__________________________________
FUEL TYPE:____________________________________
FUEL CONVERSION:

NO _______

YES_____NOTES:____________________________________________________________________________________________________________________________________

66.07%Jøtul GF 370 DV

2138914 Rev. K / 7.27.10

Table of Contents

Installation & Service Tools . .................2
Specifications................................................... 4

General Information........................................5

Safety Information . ....................................... 6

Installation
Hearth Requirements ..........................7
Clearances................................................7
Vent Requirements
Approved Vent Manufacturers.......... 8
Vertical Termination............................. 8
Masonry Chimney Conversion........... 9
Horizontal Termination......................10
Vent Termination Clearances.............11
Vent Restriction Adjustments........... 12
Vent Termination Diagram................ 13

Stove Assembly
1. Glass Frame Removal ...................14
2. Routing the Power Supply ..........14
3. Gas Connection...............................14
4. Gas Pressure.................................... 15
5. Fuel Conversion..............................16
6. High Altitude Adjustment...........18
7. Skamol Panel Installation............19
8. Reflective Panel Installation........19
9. Wishing Rock Installation............19
10. Starfire Glass Installation............19
11. Log Set Installation......................20
12. Outer Decorative Glass Panels... 21
13. System Check . .............................. 22
14. Flame Picture Adjustment...........23

Unpacking the Stove
1. Before beginning the installation, inspect the stove
for shipping damage and immediately report any
evidence of damage to your dealer.
2. Confirm stove contents.
The Jøtul GF 370 DV includes the following loose
items shipped in the Miscellaneous Hardware bag;
• 4 mm hex key - used to remove the 		front glass panel for access to the firebox.
• Remote Control Transmitter• Extension Power Cord
• M6 x 12 mm hex bolts, 4 - used with 		Outer Decorative Glass Panels.
• Propane Fuel Conversion Kit 156800
3. Confirm Firebox Components.
The firebox accessories have been packed inseparate boxes, and will include one or more of thefollowing items:
		 •
•
•
•
•

Traditional Log Set 156789
Starfire Glass 156815
Wishing Rocks 156814
Skamol Panels 156816
Reflective Glass Panels 156817

4. Remove Pallet Screw. See fig. 1.

Operation
System Overview ............................... 24
Control Functions.................................25
Wiring Diagrams................................. 28

Maintenance
Annual Cleaning..................................30.
Glass Replacement.............................30
Battery Replacement ......................... 31
Accent Lamp Replacement ............... 31
Illustrated Replacement Parts............ 32 - 35
Appendix
Mobile Home Installation................. 36
Correct Optional Flame Pictures .... 36
Waranty Statement...................................... 39

Lighting Instructions .................................. 39

Figure 1.
Pallet screw location

3

138914 Rev. K / 7.27.10

Jøtul GF 370 DV
Direct Vent Gas Stove
Manufactured and Distributed by:
Jøtul North America
Gorham, Maine USA
Jøtul AS
Fredrikstad, Norway

Test Standards

This appliance complies with
National Safety standards and istested and listed by Intertek Testing
Services of Middleton, Wisconsin.

In addition, the Jøtul GF 370
DV has been tested and listed as adirect vent gas fireplace heater and listed to
ANSI Z21.88-2005, ANSI z21.88a/CSA 2.33a-2007,
CAN/CGA 2.17-M91.

Accessories
Traditional Log Set ................................................ #156789
Wishing Rocks Set ..................................................#156814
Starfire Glass Kit ..................................................... #156815
Reflective Glass Firebox Liner . ............................ #156817
Decorative Outer Glass Panel Kit . ................... #350995
Fuel Conversion Kit, Propane - 33% TD............. #156800
Fuel Conversion Kit, Natural Gas - 33% TD........#156801
High Altitude Adjustment Kit, NG..................... #156822




Specifications

Input Rates
Natural Gas

28,000 BTU/hr. maximum input
18,173 BTU/hr. minimum input

Propane24,000 BTU/hr. maximum input
20,750 BTU/hr. minimum input

Inlet Pressure:
MIN 		MAX
Natural Gas: 5.0 WC (1.24 kPa)
7.0 WC (1.74 kPa)
Propane: 11.0 WC (2.74 kPa) 13.0 WC (3.24 kPa)
Manifold Pressure: MIN 			MAX
Natural Gas: 1.6 WC (.398 kPa) 3.5 WC (0.87 kPa)
Propane:
6.4 WC (1.59 kPa) 10.0 WC (2.48 kPa)

• Steady State Efficiency: 74.7% NG / 79.3% LP• AFUE Efficiency:

71.2% NG / 75.6% LP• CSA P4. 1-02 Fireplace Efficiency:• Intermittent Pilot Ignition ( IPI )66.70 %• Continuous Pilot Ignition Mode ( CPI or “standing 		pilot”) is available.

• Power Requirement: 120 VAC for Fan, Lamp, andBurner Control Module• Remote Control Transmitter batteries preinstalled,
3, AAA - 1.5 v• Remote Control Receiver batteries supplied: 4, AA• Fan Control Module: 120V / 60 Hz

4
Figure 2. Overall dimensions

138914 Rev. K / 7.27.10

General Information
THIS HEATER MUST BE INSTALLED AND MAINTAINED BY A QUALIFIED SERVICE AGENCY.
DO NOT ATTEMPT TO ALTER OR MODIFY THE
CONSTRUCTION OF THIS APPLIANCE OR ITS COMPONENTS. ANY MODIFICATION OR ALTERATIONWILL VOID THE WARRANTY, CERTIFICATION AND
LISTING OF THIS APPLIANCE.
WARNING: FAILURE TO POSITION THE PARTS IN
ACCORDANCE WITH THE DIAGRAMS HEREIN OR
FAILURE TO USE ONLY PARTS SPECIFICALLY APPROVED WITH THIS APPLIANCE MAY RESULT IN
PROPERTY DAMAGE OR PERSONAL INJURY.
IMPORTANT: SAVE THESE INSTRUCTIONS.

1. The installation and repair of this appliance must
be done by a qualified service person. Failure toproperly install and maintain this heater could result in an unsafe or hazardous installation, which
may result in a fire, explosion, property damage,personal injury or loss of life.

2. This appliance should be inspected before use andat least annually. More frequent cleaning may
be required due to excessive lint from carpeting,bedding material, etc. It is imperative that control
compartments, burners and circulating air passageways of the appliance be kept clean.
`S’assurer que le bruleur et le compartiment descommandes sont propres. Voir les instructions
d’installation et d’utilisation qui accompagnent
l’appareil.

3. This appliance may be installed in an aftermarket permanently located, manufactured (mobile)home, where not prohibited by local codes.
This appliance is only for use with the type(s) of
gas indicated on the rating plate. This appliance is
not convertible for use with other gases, unless acertified kit is used.

and legal installation. Some areas require a permit
to install a gas burning appliance. Always consult
your local building inspector or authority having
jurisdiction to determine what regulations apply inyour area.

In the absence of local codes, the installation requirements must comply with the current National
codes. In the U.S., these requirements are established in the National Fuel Code, ANSI Z223.1.(NFPA
54). In Canada, the codes have been established in
CAN/CGA B149 Fuel Installation Code.
Installer l’appareil selon les codes ou reglements
locaux, ou, en l’absence de tels reglements, selon
les Codes d’installation CAN/CGA-B149.

5. Do not operate this fireplace if any part of it has
been under water..

Immediately call a qualified service technician toinspect the heater and to replace any part of thecontrol system and any gas control which has been
under water.
Ne pas se servir de cet appareil s’il a ete’ plonge
dans l’eau, completement ou en partie. Appeler
un technicien qualifie pour inspecter l’appareil etremplacer toute partie du syste’me de controle ettoute commande qui ont ete plonges dans l’eau.

6. Do not operate the fireplace with the glass front
removed, cracked or broken. Replacement of theglass should be done by a licensed or qualified service person. Only remove glass for routine service.
Always handle glass carefully.
Pour utilisation avec les portes en verre cerifiers
aved l’appareil seulemend ou. Ne pas utiliser avec
des portes on verre.

7. Notify your insurance company before procedingwith installation of this fireplace.

Cetappareil peut être installé dans un maison
préfabriquée (mobile) déjà installée à demeure si
les règlements locaux le permettent.

Cet appareil doit être utilisé uniquement avec les
types de gas indiqués sur la plaque signalétique.
Ne pas l’utiliser avec d’autres gas sauf si un kitde
conversion certifié est installé.

4. The installation must conform to local codes. Your
local Jøtul authorized dealer can assist you in determining what is required in your area for a safe

5138914 Rev. K / 7.27.10

Safety Information

 Due to the high operating temperatures thisappliance should be located out of traffic andaway from furniture, draperies, etc. Maintainproper clearance to combustible mantels andfireplace trim.

 Children and adults should be alerted to thehazards of high surface temperatures and should
stay away to avoid burns or clothing ignition.

 Young children should be supervised while they
are in the same room as the appliance. Toddlers,
young children and others may be susceptible
to accidental contact burns. A physical barrier,such as a child guard, is recommended to be used
if there are at-risk individuals in the house. To
restrict access to a fireplace or stove, install an
adjustable safety gate to keep toddlers, young
children and other at-risk individuals out of theroom and away from hot surfaces.
 Any safety screen or guard removed for servicing
an appliance must be replaced prior to operating
the appliance.

 Clothing or other flammable materials should not
be placed on or near the fireplace.
 Surveiller les enfants. Garder les vêtements, lesmeubles, l’essence ou autres liquides à vapeur
inflammables lin de l’appareil.
 Never allow anyone to use the fireplace if they
are unfamiliar with its operation.

 NEVER store or use gasoline or any other flammablevapors or liquids in the vicinity of the fireplace.
 Never burn any solid materials (wood, cardboard,paper, coal, etc.) in this gas fireplace. Use withnatural gas or propane fuel ONLY.
 Any safety screen, glass or guard removed forservicing the appliance must be replaced prior tooperating the appliance.
 Do not slam or strike the glass panel.

 This appliance is NOT for use with aftermarket
glass doors. Cet appareil ne sert pas avec desportes en verre de marché des accessoires.

 Wear gloves and safety glasses while installingor performing maintenance procedures on thisappliance.       

6WARNING!

Shock Hazard. Can cause severe injury or death.
This appliance is powered by line voltage.
Do not try to repair the components in thisappliance. In no way are the component
enclosures to be tampered with or opened.
Disconnect from line voltage during
installation or performing any maintenance.

ATTENTION!
 Shut off the main gas supply to theappliance during battery replacement to thereceiver or burner control.

 Always shut off the main gas supply to theappliance during inspection, maintenance,or cleaning.

Electrical Hazards
 Be aware of electrical wiring locations whencutting holes in walls and ceilings for termination.

 This appliance power supply must be electri-

cally grounded in accordance with local codes
or, in the absence of local codes, with the current ANSI/NFPA 70, National Electrical Codeor CSA C22.1-Canadian Electrical Code.

 This appliance power supply incorporates athree-prong (grounding) plug for protection
against shock hazard and should be plugged
directly into a properly grounded three-prong
receptacle. DO NOT CUT OR REMOVE THE
GROUNDING PRONG FROM THE PLUG.

 Do not disconnect the lamp and fan powercords from the appliance power supply (FanControl Module). Use the rocker switch tocontrol power to these parts.

 Always disconnect (unplug) the main power

supply from its outlet when performing routine service on this appliance.

138914 Rev. K / 7.27.10

Installation

Stove and Vent Clearance
Requirements

Stove Location

In selecting a location for the stove, consider thefollowing points:
1) Heat distribution2) Vent termination requirements
3) Gas supply routing
4) Traffic areas, furniture, draperies, etc.
5) 120V electrical outlet availability
This stove may be located on or near conventional
construction materials, however, proper clearance to
combustibles must be maintained in order to provide
adequate air circulation around the appliance. Also, it
is important to provide adequate access around thestove for servicing and proper operation.
The clearances specified in this manual are theminimum requirements established as a result ofsafety testing. A combustible material is anythingthat can burn; i.e. sheet rock , wall paper, wood, fabrics, etc. These surfaces are not limited to those thatare visible and also include materials that may belocated behind non-combustible materials.
If you are not sure of the combustible nature ofa material, consult your local fire officials. “Fire-resistant” materials are considered to be combustible.
They may be difficult to ignite, but will burn. “Fire-rated” sheet rock is also considered combustible.

Hearth Requirements

Minimum Clearances: See figs. 3-5.
Rear:3” (76 mm) - from Rear of the unit

Corner:5” (127 mm) - from Stove Top

Ceiling:
Sides:

16 3/4” (425 mm) - from Stove Top
7” (178 mm) - from Stove Top

Minimum Clearances from the Vent Pipe
to Combustibles:
Horizontal Run:

Off the top of the pipe - 2” (51 mm) Alcove - 7” (178 mm)
Off the sides and bottom - 1” (25 mm)
Vertical Run:All sides - 1” (25 mm)



Figure 4. Alcove and Wall Clearances.

The Jøtul GF 370 DV has been approved for installation directly on combustible floor materials, including
carpeting. No additional floor protection is required,however, we recommend that the stove be installed
on a solid surface.

ALCOVE SPECIFICATIONS:
Maximum Alcove Depth:			
21 3/4” (55.2 cm)
Minimum Alcove Width:		
31 1/4” (79.3 cm)
Minimum Ceiling Height:
		62 1/4” (158.1 cm)






Figure 3. Corner Clearances.

Figure 5. Parallel Wall Clearances.

7

138914 Rev. K / 7.27.10

Venting Requirements

There are three types of venting configurations approved for use with this appliance:• Vertical Venting / Vertical Termination• Vertical Venting / Horizontal Termination• Horizontal Venting / Snorkel Termination

This appliance is approved for use with the 4/6
direct vent systems manufactured by the companies
listed on page 8. Use parts of one manufacturer only
- DO NOT MIX VENT COMPONENTS FROM DIFFERENTMANUFACTURERS WITHIN THE SAME SYSTEM.

Installation of any components not manufactured or approved by Jøtul or failure to meet all clearance requirements will void all warranties and could
result in property damage or bodily injury.

The approved vent configurations describedin this manual are derived from extensive testingunder controlled laboratory conditions. Gas appliance
performance can be negatively affected by variables
present in the installation environment, i.e.; atmospheric pressure, strong prevailing winds, adjacentstructures and trees, snow accumulation, etc. These
conditions should be taken into consideration by the
installer and stove owner when planning the ventsystem design.

Approved Vent Manufacturers

The Jøtul GF 370 DV stove is approved for installation
with direct vent chimney components supplied by
the following manufacturers:
Simpson Dura-Vent, Inc.
P.O. Box 1510
Vacaville, CA 95696-1510		

800-835-4429

Selkirk Corporation
1301 W. President George Bush Hwy, Suite 330
Richardson, TX 75080-1139
800-992-8368
American Metal Products (Amerivent)
8601 Hacks Cross Rd.
Olive Branch, MS 38654 		
800-423-4270

Security Chimneys International Limited
2125 Monterey, Laval, Québec
Canada, H7L 3T6			
450-973-9999
Metal-Fab, Inc.
P.O. Box 1138
Wichita, KS 67201		

316-943-2351

ICC, Inc.
400 J-F Kennedy St. Jerome, Quebec
Canada, J7Y 4B7			
450-565 6336

IMPORTANT• JOINT SEALINGREQUIREMENT:APPLY A 1/8” BEAD
OF HIGH-TEMPERA
TURE SEALANT OR
MIL-PAC® TO THE MALE
SECTION OF THE INNERVENT PIPE. THE CEFigure 6.
MENT SHOULD FORM
A SEAL BETWEEN THE
INNER AND OUTER PIPES. SEE FIG. 5. SEE VENT MANUFACTURER’S INSTRUCTIONS.
• NEVER MODIFY ANY VENTING COMPONENT, OR
USE ANY DAMAGED VENTING PRODUCT.

• THE GAS APPLIANCE AND VENT SYSTEM MUST BE
VENTED DIRECTLY TO THE OUTSIDE OF THE BUILDING AND NEVER ATTACHED TO A CHIMNEY SERVING A SOLID FUEL OR GAS BURNING APPLIANCE.
EACH DIRECT VENT GAS APPLIANCE MUST HAVEITS OWN SEPARATE VENT SYSTEM. COMMON VENTSYSTEMS ARE PROHIBITED.
• IF VENTING SYSTEM IS DISASSEMBLED FOR ANY
REASON, REINSTALL PER THE MANUFACTURER’SINSTRUCTIONS PROVIDED FOR THE INITIAL INSTALLATION.

Vertical Venting and Termination

The Jøtul GF 370 DV can be vertically vented througha roof or ceiling. Follow these guidelines

 Steep roofs, nearby trees, or predominantly windy
conditions, can promote poor draft or down
draft conditions. In such cases, an increase to theheight of the vent may improve performance.

 If an offset or elbow is necessary in the verticalrise, the vent pipe must be supported every three feetto avoid excessive stress on the offsets. Use listed Wall
Straps from any of the approved vent suppliers.

 A maximum of two 90° or four 45° elbows may be
used in a vertical termination. Whenever possible,use 45° elbows instead of 90° elbows as they
offer less restriction to the flow of flue gases andintake air.

 A listed firestop is required at any floor penetration. The opening should be framed in according
to the manufacturer’s instructions.

 Always maintain a minimum 1" clearance from all
sides of the vertical vent system to any combustible material.

 Minimum vertical termination height: 6 ft. ofvent pipe.

8Horizontal Overhang

18.
min.

Termination
Cap

18.
min.

Vertical Wall

138914 Rev. K / 7.27.10#991 Vertical Termination Cap

Lowest Discharge
Opening

Cap Adaptorincluded in#934 Kit

Exhaust Gas

Intake Air

18 min.

Figure 7. Minimum roof penetration height and clearance
from adjacent surfaces - verticaltermination.

 IT IS NECESSARY to add restriction to a vertical ventinstallation to compensate for excessive draft. See
page 13; Exhaust Restriction Adjustment.

 GAS VENT HEIGHT: In no case shall any discharge

4” Flex Pipe
not included
in kitSupport/Wall
Thimble Cover- included
in#934 Kit

Use Standard
Simpson DuraVent GS Pipefrom stove tothimbleopening on the cap be less than 18” (457 mm) horizontally from the roof surface. See fig. 7.

 Maximum Vent Height: 35 ft. above the appliance.

Masonry or Prefabricated Chimney
Conversion

The GF 370 DV is approved for use with direct ventchimney conversion kits in a masonry chimney ora prefabricated solid fuel listed chimney. These areavailable from any of the manufacurer’s listed on
page 8.

Figure 8. Vent System through a masonry chimney
using the Simpson Dura-Vent Chimney Conversion Kit#934. Other manufacturers use similar designs. May
also be used in listed prefabricated chimneys.

The following installation requirements must be
followed:
1. Use the restrictor zone guidelines in the Vent
Window Diagram, fig. 17. In masonry chimney, afireclay liner or listed steel liner, must be present
the entire length of the chimney.

3. Overall venting should not exceed 35 ft. (10.67 m).
4. The liner must have an inside dimension of 6”
round or greater.

5. Prefabricated chimneys must be UL 103 or ULC
S-629 listed and have a minimum INSIDE diameter of 6 inches, (150 mm). Prefabricated chimneys
must be listed for the specific manufacturer’s
conversion kit.

IMPORTANT NOTICETHE USE OF AN EXISTING CHIMNEY AS AN AIRINTAKE IS NOT COVERED UNDER THE ANSI
Z21.88-1999-CSA 2.33-M99 TEST METHODSAND RESULTING ITS/WHI PRODUCT CERTIFICATION. THE CODE AUTHORITY HAVINGJURISDICTION MUST BE CONSULTED PRIORTO PROCEEDING WITH THIS INSTALLATIONMETHOD.

9

138914 Rev. K / 7.27.10

Horizontal Termination

 Minimum vertical rise from the vent collar is a 24”
section vent pipe. See fig. 9. Minimum horizontal
run is 12” with natural gas and 18” with propane.

Figure 9. Minimum ventpipe sections required forhorizontal termination:
A = 12” with NG
18” with LP A maximum of two 90° or four 45° elbows may

be used in a horizontal termination. Wheneverpossible, use 45° elbows instead a 90° elbow as
they offer less restriction to the flow of flue gases
and intake air. Reduce the overall horizontal run
by 4 feet for each 90° elbow, and 2 feet for each 45°
elbow.

Listed Wall
Thimble

 Snorkel Termination - ( 14” or 36”):

NATURAL GAS ONLY. DO NOT USE SNORKELTERMINATION WITH PROPANE FUEL.
A horizontal vent run may be made with a 90°
elbow directly to the rear of the stove only whenterminated by a 14 or 36 inch snorkel cap. Fig. 10shows the minimum vent pipe requirements.

14” Snorkel: The maximum horizontal vent run
must not exceed a 24” section of pipe and must bea minimum of 12”.
36” Snorkel: The maximum horizontal vent run
must not exceed 5 feet and must be a minimumof 12”.

Figure 10. Minimum ventpipe sections required for a 14”
Snorkel termination - Natural
Gas ONLY.
.





 The termination cap must not be recessed into

the wall or siding. Do not fill air space in wall aroundtermination cap with any type of insulation.

Listed Wall
Thimble Wall Cut-out: A minimum 10” X 10” square holeis adequate for proper pipe clearance through awall, provided the vent is positioned to maintain2” minimum clearance at the top. A 1” minimum
clearance must be maintained to combustible
material around the other sides. See fig. 11.

 Any horizontal run of vent must have a 1/4” rise forevery foot of run toward the termination cap.

 All horizontal terminations must comply with theclearance specifications to adjacent structures as
indicated in fig. 12.

 Installation of a Vinyl Siding Standoff is required
to prevent damage to vinyl siding between thevent cap and the exterior wall.

 A horizontal termination cap must maintain a 3”

clearance to any overhead combustible projections thatare 2 1/2” or less. It must also maintain a 12” clearance
from projections that exceed 2 1/2”. See fig. 13.
Vinyl siding projections require a default clearance of18” to the vent terminal.

10
 

Figure 11. Install alisted wall thimble
according to manufacturer’s instructions
to maintain required
clearance to combustible materials.

138914 Rev. K / 7.27.10

Figure 12. Horizontal termination clearances

A = Clearance above grade, veranda, porch , deck, or balcony: 12 inches (30 cm) minimum.

B = Clearance to window or door that may be opened:**Min. 9 inches, U.S. / *12 inches (30 cm) CAN.
We recommend 12 in. minimum to prevent condensationon the window.
C = Clearance to permanently closed window:**Min. 9 inches, U.S. / *12 inches (30 cm) CAN
We recommend 12 in. minimum to prevent condensationon the window.
D = Vertical clearance to ventilated soffit located above theterminal within a horizontal distance of 2 feet (60 cm)
from the center line of the terminal: 18 inches(46 cm) minimum.
E = Clearance to unventilated soffit: 12 inches (30 cm)
minimum.

F = Clearance to outside corner: **Min. 9 inches, U.S. / *12
inches (30 cm) CAN. We strongly recommend 12 inches,particularly where windy conditions prevail.
* In accordance with CSA B149 Installation Codes.
** In accordance with the current ANSI Z223.1/NFPA 54, National
Fuel Gas Code. Note: Local Codes and Regulations may requiredifferent clearances.





G = Clearance to inside corner: ** Min. 6 inches, U.S. / *12
inches (30 cm) CAN. We strongly recommend 12 inches,particularly where windy conditions prevail.

H = *Not to be installed within 15 feet (4.5 m) above a meter/regulator assembly within 3 feet (90 cm) horizontallyfrom the center line of the regulator.
I = Clearance to service regulator vent outlet:
3 feet (91 cm) minimum.

J = Clearance to non-mechanical air supply inlet to buildingor the combustion air inlet to any other appliance:
12 inches (30 cm) minimum.
K = Clearance to a mechanical air supply inlet:**Min. 3 feet (91 cm) above if within 10 feet horizontally,
U.S. / *6 feet (1.83 m) minimum / CAN
L = 1 Clearance above paved sidewalk or a paved driveway
located on public property: 7 feet (2.1 m) min.
M = Clearance under veranda, porch, deck, or balcony:
12 inches (30 cm) minimum. 2

A vent shall not terminate directly above a sidewalk or driveway
which is located between two single family dwellings and serves
both dwellings.
2
Only permitted if veranda, porch, deck, or balcony, is fully open
on a minimum of two sides beneath the floor.*1




Figure 13.
Termination clearance to overhangs.

11138914 Rev. K / 7.27.10

Vent Restriction Adjustments
The Jøtul GF 370 DV features adjustment controls forboth intake air and exhaust to accommodate a varietyof conditions that result from variables inherent in thevent configuration and environment. Both controls
can be accessed from outside the firebox to allow theburner to be “dialed-in” under operation. See figures 14
and 16.
Use the Vent Termination Diagram, fig. 17, to
determine which zone your vent termination falls
within and make the appropriate exhaust and air
intake setting adjustments. Use these settings as
general guidelines to start from. The final settings
will ultimately be determined by the individual
characteristics of your particular installation.
There are no hard and fast rules.

Exhaust Vent Restriction

Exhaust restriction prevents overly strong draftthat can interfere with pilot function, cause poor
combustion or a weak flame picture. The shutter is
set in the fully open position at the factory. The final
position of the restriction shutter is determined bywhere the vent termination falls within the ventwindow diagram.
For example, if the vent rise is 20 feet andincludes one elbow in a horizontal run of 5 feet, theappropriate exhaust setting will be Full Restriction.

Exhaust Restrictor Adjustment

1. Remove the Trim Rings from the Top Plate.

2. Loosen the locking screw and turn the restrictor
pivot plate to the appropriate indicator point as
specified in the vent window diagram, figure 17.
After the burner has been operating for 15 minutes,
make any further adjustment in 1/8” increments
until the desired flame picture is achieved. Do not
exceed the fully closed setting as shown in fig. 15.
Operate the burner for 10-15 minutes between additional adjustments.
3. Tighten the locking screw and replace the Trim
Rings.

Intake Air Adjustment

An Intake Air shutter plate allows further burneradjustment for taller vent runs. It is located under thefirebox floor and is set fully open at the factory. See
fig. 16.

The shutter has an adjustment range of 1 inch.
To change the setting, loosen the wingnut and slide
the gasketed shutter stem backward to the half or
fully closed positions, depending on which vent zone
is appropriate. Retighten the wingnut before lighting
the burner to seal the gasket. Allow the flame pattern
to settle in for 10- 15 minutes between each settingchange.

Zone DTop Plate

Vent terminations within Zone D are susceptible
to draft conditions that may interfere with theintermittent Pilot Ignition functionality. In suchcases, we recommend that the stove be operated
only in Continuous Pilot Ignition mode.

Pivot Plate

Figure 14. The Exhaust Restrictor is located within thevent adaptor collar.











  
Figure 15. Exhaust Restrictor settings

12

Figure 16. Air intake shutter location.

138914 Rev. K / 7.27.10

 A maximum of two



90° or four 45° elbows
may be used. Whenever possible, use 45°
elbows instead of 90°
elbows as they offer less restriction to
the flow of flue gases
and intake air. Use ofelbows may adversely
affect IPI functionality. In such cases, CPI
mode should be used.

 
     

 Reduce the overall

elbows are used in ahorizontal run, a lessrestricted setting may
be more effective thanthat indicated by thetermination zone diagram.



horizontal run by
4 feet for each 90°
elbow, and 2 feet foreach 45° elbow.

 When two or more

Intake Air - Fully Closed
Full Exhaust Restriction



Intake Air - Half Closed
Half Exhaust Restriction

   ­  Intake Air - Fully OpenNo Exhaust Restriction


 
   

ANY VENTING WITH A VERTICAL RISE MUSTTERMINATE (END) WITHIN THE SHADED AREAS.







           Figure 17 . Vent Termination Diagram.

13

138914 Rev. K / 7.27.10

Stove Assembly
1. Glass Frame Removal

To access the firebox, use the 4 mm hex key toremove the four socket head screws that attach theglass frame to the firebox. See fig. 18.

2. Routing the Power Supply

The power cord located in the valve compartment isconnected to the Fan Control Module which is themain power supply for all stove operating functions.
Route the cord through the pedestal and out the rearof the pedestal base as in fig. 18, or through the floor.
CAUTION: Take care that the pedestal base does notpinch the power cord. You should be able to feel freeplay in the cord.

The 10 foot extension power cord, supplied in
the hardware bag, is intended to connect the interior
cord to the nearest 120V house current outlet.

Figure 18.
Glass frame
removal.

DO NOT CONNECT THE STOVE TO HOUSE CURRENT UNTIL THE INSTALLATION IS COMPLETE AND
YOU ARE READY TO INITIATE THE FIRST BURN.

3. Connecting the Gas Supply
Gas Supply Requirements

ALL INSTALLATIONS MUST COMPLY WITH LOCALCODE OR IN THE ABSENCE OF LOCAL CODE, MUSTCOMPLY WITH THE MOST RECENT EDITION OF THE
NATIONAL FUEL GAS CODE ANSI Z223.1/NFPA 54 OR
CAN-B149.
THIS PRODUCT MUST BE INSTALLED BY A
LICENSED MASTER OR JOURNEYMAN PLUMBER
OR GAS-FITTER WHEN INSTALLED IN THE
COMMONWEALTH OF MASSACHUSETTS.

Shut-off ValveAll codes require a gas shut-off valve (gas cock)and union to be installed in the supply line within 6feet of the appliance. This allows for the disconnection of the stove for servicing and maintenance. See
Fig. 19.
A T-HANDLE GAS SHUT-OFF VALVE IS REQUIRED IN MASSACHUSETTS IN COMPLIANCE
WITH CODE 248CMR.

14

The stove and gas control valve must be disconnected from the gas supply piping during any pressure testing of the system at test pressures in excess
of 1/2 psig. For pressures lower than 1/2 psig, isolate
the gas supply by closing the manual shut-off valve.

Control Valve Connection

The gas supply line connection to the stove flexline can be made at the rear of the base plate or
through the floor. The gas supply line should be aminimum 3/8” inside diameter, or the appropriate
size to provide sufficient gas pressure to the valve
regardless of the input setting.

The use of flexible gas appliance connectors is acceptable in many areas in the U.S. In Canada, methods
vary depending on local code. If local codes permit,
use flexible gas line for ease of installation and service. For those locales where flexible gas lines are notpermitted, use the 3/8” iron fitting to make the connection at the top side of the Control Valve. See fig. 19.
Secure all joints tightly using appropriate tools
and sealing compounds (for propane units, be sure touse compounds that are propane resistant). Turn on
gas supply and test for gas leaks using a 50/50 soapy
water solution or a gas detector.

138914 Rev. K / 7.27.10
 



   

Inlet Pressure
MIN 		MAX
Natural Gas: 5.0 WC (1.24 kPa)
7.0 WC (1.74 kPa)
Propane: 12.0 WC (2.99 kPa) 14.0 WC (3.48 kPa) 


 

Manifold Pressure
MIN 		MAX
Natural Gas: 1.6 WC (0.398 kPa)
3.5 WC (.87 kPa)
Propane:
6.4 WC (1.59 kPa) 10.0 WC (2.48 kPa) 



 

Figure 19. Gas supply valve types and fittings.
NEVER USE AN OPEN FLAME TO CHECK FOR GASLEAKS.
ALWAYS REFER TO THE LIGHTING INSTRUCTIONSON THE INSIDE BACK COVER OF THIS MANUAL
WHEN LIGHTING THE STOVE.

Soap Solution Leak Test

• Mix a 50-50 solution of water and dish soap.

• Light appliance - see lighting instructions on theback cover of this manual or on the rating plate.

• Brush or spray all joints and connections with thesoapy water solution.

• If bubbles appear at any connection or seam or agas odor is detected, immediately turn gas control
knob to the OFF position.
Tighten or reconnect the leaking joint and retest
for any gas leaks.

4. Testing Gas Pressure

Proper gas pressure provides a consistent flow of gas
to the appliance and is instrumental in checking for
gas leaks. There are two pressure test points on thefront of the stove control valve where test gauge connections are made. See Fig. 20. Gauge connections
are identified by:• E for inlet or supply pressure ( the amount of gas
coming to the valve.)• A for manifold pressure (the amount of gas that iscoming out of the valve to the burner.)
The line must be disconnected from the gas supply line by closing the main supply manual gas shutoff valve (gas cock) during any pressure testing of thegas supply piping system that is equal to or exceeds
pressures of 1/2 psig (3.5 kPa).

ALWAYS TEST PRESSURES WITH VALVE REGULATORCONTROL AT THE HIGHEST SETTING.

Symptoms of incorrect gas pressure include:
Insufficient gas pressure:• Small pilot flame which can result in insufficient
millivolts.

• Little variation in flame picture between HI and LO
regulator settings.
• Insufficient gas to support more than one appliance causing nuisance outages or gas surges.

Excessive gas pressure:• Permanent damage to valve causing complete appliance shut down.
• Too large a pilot flame resulting in overheating of
the power generator and consequent shut down.

• Sooting due to impingement and/or incorrect fuelto air mix.

A Manifold

E InletPilot Adjustment

Figure 20. Pressure test points located on the frontof the valve.
WARNING
DO NOT ALLOW THE INLET GAS PRESSURE TO
EXCEED 14.0” WC (OR 1/2 PSIG) AS SERIOUS
DAMAGE TO THE VALVE MAY RESULT.

15

138914 Rev. K / 7.27.10

5. Fuel Conversion

The GF 370 DV gas stove is shipped from the factoryequipped to burn Natural gas. Propane fuel conversion kit 156800 is included with the stove to enable
use with LP gas if necessary. The kit contains all thecomponents needed to complete the task and ensure
safe operation, including labels that must be affixed
to the stove.

CAUTION: Before proceeding with this conversion,
the gas supply must be shut off prior to disconnecting
the electrical power.
This conversion kit shall be installed by a qualified
service agency in accordance with the manufacturer’s
instructions and all applicable codes and requirementsof the authority having jurisdiction. If the information in these instructions is not followed exactly, a fire,
explosion, or production of carbon monoxide may result
causing property damage, personal injury or loss of life.
The qualified service agency is responsible for the proper
installation of this kit. The installation is not proper andcomplete until the operation of the converted applianceis checked as specified in the manufacturer’s instructions
supplied with the kit.
Cet équipement de conversion sera installé par une
agence qualifiée de service conformément aux instructions du fabricant et toutes exigences et codes applicables de l’autorisés avoir la juridiction. Si l’information
dans cette Instruction n’est pas suivie exactement, un
feu, explosion ou production de protoxyde de carbone
peut résulter le dommages causer de propriété, pert ou
blessure personnelle de vie. L’agence qualifiée do service
est esponsable de l’installation propre de cet équipemetn. L’installation n’est pas propre et complète jusqu’à
l’operation de l’appareil converi est chéque suivant lescritères établis dans les instruction de propriétaire provision nées avel l’équipement.

Conversion Kit(LP #156800, NG #156801)

Tools required:• 1/2” & 13 mm open end wrench or deep-well socket• Torx T20 or slotted screwdriver• 7/16” open end wrench • 1/4” nut driver• 4 mm allen wrench• 3 mm allen wrench• Label B - apply to the rating plate in the space indicated on the plate.
• Small valve label - apply to valve body
• Conversion instructions

Fuel Conversion Procedure
1.

Turn off gas supply to the stove and disconnect
from electrical power source.

2. Remove the glass frame. See fig. 18.

3. Loosen the primary air shutter wingnut and push
the stem all the way back. Fig. 21.




Figure 21.
4. Pull the Burner Plate forward to disengage it fromthe burner orifice and lift it out of the firebox.

5. Locate the main burner injector. See fig. 23 on
page 17. Slide the Air Shutter out of the way anduse a 1/2” open end wrench or deep-well socket toremove the burner orifice from the brass orificeholder. Replace with the orifice supplied in thekit. Tighten securely.
6. Change the Air Shutter position: Lift the shutter
tube up in its hinge pin slots and turn the tube
over, so that the appropriate fuel type indicator(LP or NG) is oriented facing you. See fig. 22. Push
the shutter all the way back over the injector.

7. Change the Pilot Orifice. Pull the Pilot Hood off of
its base. It will snap by the retainer clip shown in
Fig. 23.

Conversion Kit Contents:• 1 regulator tower labeled for the appropriate fuel• 2 regulator tower Torx screws• 1 burner injector (#38 mm for NG, #53 for LP)• 1 pilot orifice (#62 for NG, #35 for LP)• Label A - to be completed and applied to the baseof the valve compartment

16

Figure 22. Primary air shutter orientation must bechanged for fuel type.

138914 Rev. K / 7.27.10

Pilot Head

Ignitor

Pilot Orifice

Flame Sensor

Primary Air
Shutter
Retainer Clip

Injector
Regulator
Diaphragm
Tab & Receptacle
Terminals

elApply Lab“A” Here

Regulator
Tower
Use new Torx
screws supplied

Figure 23. Fuel conversion components and assemblies
Using a 4 mm allen wrench, unscrew the pilot
orifice. Replace it with the orifice from the kit.
Be sure the new orifice is tightly secured to prevent by-pass leakage.
Replace the pilot hood by simply pushing itback into place on its base.

8. Reinstall the Burner Plate by engaging the venturi tube with the Air Shutter. BE CERTAIN THE
BURNER IS LEVEL AND SECURELY SEATED ON THE
SUPPORT LEGS ON THE FIREBOX FLOOR.

9. Replace the variable regulator. Using a Torx T-20
screwdriver, remove the two specialty screws
from the regulator tower on the front of thevalve. Note: To help identify which screws to remove,refer to the new regulator in the kit. See fig. 23.
10. Disconnect the Regulator wire lead from thereceptacle housing terminal. Remove the regulator tower and the rubber diaphragm.

11. Install the new variable regulator tower from thekit. Be sure that the gasket is properly positioned
and tighten screws securely. Connect the wire lead.
12 . Apply the identification labels to the stove so that they canbe seen by any person that may be servicing the stove.
• Label “A”: Apply to front lip of the valve compartment.
• Label “B”: Apply to the Rating Plate.
• Small valve sticker: Apply to valve.

13. Install the accessory panels and burner media as
appropriate. See pages 19-21.

14. Apply anti-seize lubricant to the socket head glass
frame screws before reinstalling the glass frame.
15. Apply gas to the system and check for leaks using
a soapy water solution or gas sensor.
16. Follow the System Check instructions on pages 22-23
for initial start-up and flame picture adjustment.

17

138914 Rev. K / 7.27.10

6. High Altitude Adjustment
The decreased atmospheric pressure of higher altitudes affects heat value of gaseous fuels. Most gas
suppliers derate the gas intended for use at elevations above 2000 feet. Check with your gas supplier
before performing derate adjustment to the burner.

This appliance may be adjusted for altitude over2000 ft. (610 - 1371 m) for natural gas.
If the gas supplier does not derate fuels, install High
Altitude Adjustment Kit 156822 for Natural gas.
DO NOT DERATE FOR PROPANE.
U.S & Canada per
ANSI Z21.88-2005•CSA 2.33-2005, CAN/CGA 2.17

For natural gas installations from 610-1370 meters(2000-4500 ft.) the orifice size (DMS) is #39. Seedata plate for additional information. For highaltitude installations consult the local gas distributoror the authority having jurisdiction for proper rating
methods. If the installer must convert the unit toadjust for varying altitudes, the information sticker
must be filled out and applied to the appliance at thetime of the conversion.
Cet appareil est equippé pour des altitudes compries
entre 0 et 2000 pieds (0-610 m ) seulement.

Derating Procedure• Follow Steps 1-6 of the Fuel Conversion procedureon pages 16 to change the burner injector. Use theinjector supplied with the kit. Detailed instructions are also included in the kit.
• Conduct gas leak and gas pressure tests as detailed on page 15 of this manual.

• Conduct system check and flame picture adjustments as specified on pages 22-23.
INSTALLER: Fill out the appropriate information
and apply the high altitude conversion label provided to the rating plate on the appliance. See fig. 24.
This appliance has been converted for use at analtitude of___________ .
Orifice Size: __________ Manifold Press. _______
Input Btu/Hr. _________ Fuel Type ___________
Date: ___/___/___ Converted by:_____________
Cet appreeil a été converti au _____ Injecteur_____
Pression à la tubulure d’alimentation ___________
Déoit calorifique ___________
Figure 24. High Altitude Conversion Label.

18

7. Firebox Panel Installationfor Skamol Panelsand optional
Reflective Glass Kit 156817

You will need to remove the pilot hood and burnerplate to provide clearance to install either panel kit.
Pull the pilot hood off of the pilot base - it will slip
past its retainer clip. Simply lift the burner up and outof the firebox.

Skamol Panels

DO NOT OPERATE THIS STOVE WITHOUT THE SKAMOL PANELS INSTALLED. If desired, the panels may be
painted black using any high-temperature paint.
1. Install the Rear Panel.
Orient the panel with the bevelled edges facing
back, matching the angles of the firebox walls.
Tilt the panel to engage the upper edge behind
the two retainer brackets at the top of the firebox. Push the panel all the way back and centeredagainst the firebox wall. See fig. 25a.
2. Install the Side Panels.
Orient each panel with the rounded edge facing
forward. Tilt the panel to engage the upper edge
behind the retainer clip at the top of the firebox.
See fig. 25b.

3. Replace the burner plate. When properly located, it
will be level and secure.
4. Replace the pilot head. It will just snap back into
place on the base.

Reflective Glass Panels

Use the cotton gloves to handle the panels to prevent
fingerprints on the surfaces. Fingerprints are difficult
to remove. Use a clean cloth to remove any dust fromthe glass panels.
1. Use pliers to bend down the center tab of eachretainer bracket. This is the “keeper” for the sidepanels which will, in turn, hold the rear panel inplace. See fig. 26a.

2. Orient the rear panel, shiny side out, textured sidein. Tilt the panel to engage its upper edge behind
the retainer brackets. Be sure it is pushed all the way
back and centered. See fig. 26b.

3. Orient the side panels, shiny side out, and slideeach behind the center tab of the retainer bracket.
See Fig. 26c.

4. Replace the burner plate. When properly located, it
will be level and secure.
5. Replace the pilot head. It will just snap back into
place on the base.

138914 Rev. K / 7.27.10
Retainer Brackets

Figure 25a.
Install Rear Skamol
Panel.
Figure 26a.
Bend center tab toretain glass panels.

Rear Skamol Panel

Figure 26b.
Install Rear Glass
Panel.
Figure 25b.
Install Rear Skamol
Panels.
Side Skamol PanelSide Skamol Panel

Rear Glass Panel

Wishing RockCAUTION: THE ROCKS ARE FRAGILE! SUPPORT THE
ASSEMBLY FROM THE BOTTOM AND HANDLE CAREFULLY!

Side Glass Panel

8. Install Burner MediaSide Skamol Panel

Figure 26c.
Install Side Glass
Panels.

1. Engage the Wishing Rock bed with the two center
burner pins as shown in fig. 27.

2. Evenly disperse the Ember Stones supplied overthe burner plate around the log parts. DO NOTALLOW EMBER STONES TO BLOCK THE PILOT ASSEMBLY AREA. The carry-over ports directly in frontof the pilot must remain clear for proper pilot
ignition. See figs. 29 and 65 for examples.

Starfire Glass

Do not use more than the four pounds (in two, 2 lb.
bags) of glass media provided. For best results, evenly
spread the contents of the bag over the entire burnerplate and rear skirt, mounding a crown toward thecenter. DO NOT COVER THE AREA IMMEDIATELY IN
FRONT OF THE PILOT ASSEMBLY. The carry-over ports
directly in front of the pilot assembly must be clear toensure proper pilot ignition. See fig. 66 page 34.

Figure 27. Set Wishing Rock assembly on pins.

19

138914 Rev. K / 7.27.10

Install the Log Set

The three-piece log set includes a bag of ember
stones that simulate glowing coals when the burneris operating.
Use workgloves and handle the individual logs
carefully, supporting each with both hands. Install
the Logset and Ember Stones as shown in figures
28-31.

Figure 30. Engage the Left Log with the rear burnerplate pin.



Figure 28. Engage the Bottom Log with the twocenter pins in the burner plate.

Figure 31.

Evenly disperse the Ember Stones evenly over theburner plate around the log parts. DO NOT ALLOWEMBER STONES TO BLOCK THE PILOT ASSEMBLY AREA.
The carry-over ports directly in front of the pilot mustremain clear for proper pilot ignition.

Figure 29. Lean the Right Log up against the upper
right corner of the firebox and engage its toe with theindentation in the Bottom Log.

20

Replace the Glass Frame.

Reinstall the glass frame using the 4 mm hex key
and socket head screws previously removed.

138914 Rev. K / 7.27.10

9. Exterior Decorative
Glass Panel Kit Assembly
Kit Contents
1. Upper Side Brackets, 2
2. Lower Side Brackets, 2
3. Upper Front Bracket
4. Lower Front Bracket
5. Side Glass Panels, 2
6. Front Glass Panel
7. Top Glass Panel

IMPORTANT!

Clean the inside surface of the glass before installation.

8. Top Plate
9. 3 mm hex key
10. 4 mm hex key
11. M8 x 40mm bolts, 4
12. M6 x 20 FH screws, 4
13. Friction Buttons, 8

Use the white gloves supplied when handling glass
to minimize fingerprints.

13

12

3

10
9
7

6

Before mounting the support brackets to the stove
set each on the end of the glass panel and bend thebracket tabs to hold the panel securely.
See Detail A, fig. 32.
1. Remove the top plate from the stove.

2. Install the Upper Side brackets using the four M8 x 12 mm
hex bolts supplied in the Miscellaneous Kit that camewith the stove.

There are two versions of the side brackets. The upper bracket to be mounted on the right side is thesame as the lower bracket to be mounted on the left
side. The upper bracket on the left side is the sameas the lower bracket on the right side.See fig.32.

3. Remove the door handle from the door as shown infig. 30. Attach the lower front bracket to the door
using two M6 x 20 socket screws and the 4 mm hex
key. Replace the door handle assembly using the #2
and #4 hole locations to move the handle forward toalign with the glass panel.
4. Place the glass panel in the lower bracket and attach
the upper front bracket the top of the door using theremaining M6 x 20 screws.
5. Set the new cast iron top plate in place and replace
the center grate halves.

84

1

6. Place a friction button at each corner of the top plate andset the glass top plate in position.

Longer section of brackets
point to rear of stove5

M8 x12 hex bolts

Figure 33. Upper side bracket bolt locations.

112

Lower Bracket

Longer section points torear of stove
Door Handle
Bend tab at endof bracket to holdpanel securely.

Figure 32. Exterior Decorative Glass Kit contents.

Figure 34.
Door handle after lower front bracket is installed.

21

138914 Rev. K / 7.27.10

10. Initial System Check

The burner and fan control system consists of the following built-in or supplied components:
1) Remote Transmitter - 3, AAA batteries preinstalled
2) Remote Receiver - 4, AA backup batteries preinstalled
3) Fan Control Module - switched
4) Pilot Mode Switch - with 1, 9V backup battery

All internal connections have been made at thefactory. The remote controls are preprogramed andthe entire system tested.
NOTE: Check the build date on the shipping
crate label. If it has been more than 6 months
since the build date, be prepared to replace
the Receiver and Transmitter batteries.

Open outlet- not used

4. PURGING THE GAS LINE: Open the gas supply
valve. When lighting the appliance for the firsttime it will take a few moments to clear the gasline of air. Once the purge is complete, the pilot
light will ignite.

5. PILOT FLAME: The pilot flame should be steady not lifting or floating. The flame should be blue incolor around the pilot hood, with traces of yellow
toward the outer edges. It is important that thepilot flame engulf the top 1/8” of the flame sensor. The pilot flame should project out of the pilot
hood 1” from both ports extending to reach theburner plate ports. See fig. 36. The pilot flame canbe tuned by turning the adjustment screw locatedon the front of the valve. See fig. 20.
6. INSTALLER PLEASE NOTE:CHECK FUNCTIONALITY. The burner, remotecontrol and fan functions have each been tested
at the factory. However, it is important to run
through each function and be sure to familiarize
the homeowner with the operation procedures.
See the Operation section on pages 24-27 fordetails regarding Remote Control functions andsettings.

22







= POWER ON= POWER OFF
Figure 35a. Fan Control Module power switch.

CPI / Continuous Pilot Ignition(Standing Pilot)
OR

1. Connect the power extension cord to the interior
power cord and to a 120V electrical outlet.

3. Slide the Remote Receiver switch to the ON position. The ignitor will generate spark in either IPI or
CPI pilot modes. See fig. 35b.

toAccent Lamp

Follow this procedure for the initial system check following installation:

2. Turn the Fan Control Module rocker switch to the
ON position, fig. 35a. It is located in the valve compartment, behind the Receiver control box.

to
Fan

IPI / Intermittent Pilot Ignition 
Remote Receiver
SwitchFigure 35b. Initial system settings.

IgnitorFlame Sensor

Carry-over Ports
Figure 36. Correct Pilot flame pattern.

138914 Rev. K / 7.27.10

Flame Appearance / Air Shutter
Adjustment		WARNING:AIR SHUTTER ADJUSTMENTS SHOULD ONLY BE
PERFORMED BY A QUALIFIED, PROFESSIONALSERVICE TECHNICIAN.
Locate the Primary Air Shutter control under the firebox floor above the gas valve. See fig. 37. The shutter
is set at the midpoint of its adjustment range at thefactory. This will give good results in the majority of
installation configurations, however, you may needfind it necessary to adjust it to get the best flame
picture depending upon the your specific installation.
With the burner operating, loosen the wingnut
on the shutter stem. Push the stem back toward therear of the stove will decrease combustion air. Pull it
forward to increase air.

Generally, flame appearance is a matter of individual preference, however a warm yellowish flame ismost common.

 Closing the air shutter - in extreme cases may

generate very long yellow flames resulting in soot.
Sooting produces black deposits on the logs, on theinside walls of the appliance, and potentially on
the exterior termination cap.
Sooting is caused by incomplete combustion in the
flames and lack of combustion air entering the air
shutter opening.

 Opening the air shutter - will generate a flame thatis blue and transparent, or “anemic”. This flame isgenerally more efficient, but not as attractive.

 Allow the burner to operate at the highest settingfor 20-30 minutes before making any adjustments.
Always make adjustments in 1/8” increments andallow the burner to settle-in for 10- 15 minutes
between additional adjustments.




Figure 37. Primary Air Shutter location.

Figure 38. Proper flame picture -Traditional Logs.
Alternate flame pictures for Wishing Rock and Starfire
Glass are illustrated in figs. 67 & 68 in the Appendix on
page 36.

Operation Notes

1. For the first several hours of operation, it is common to detect some odor as the metal and manufacturing materials cure under heat. This conditionis temporary and can be alleviated by allowing
plenty of fresh air to circulate through the area.

2. Condensation may develop on the glass upon eachlighting of the appliance. This “fog” will disappear
as the glass heats.

3. Keep the controls and the area under the appliancefree of dust. Always keep the appliance area clear
and free from combustible materials, gasoline andother flammable liquids.
4. This appliance can be operated with a continuously burning pilot flame. Exercise caution whenusing household products containing combustible
vapors.

5. CAUTION: DO NOT OPERATE THIS APPLIANCE
WITH THE GLASS REMOVED, CRACKED OR BROKEN.
REPLACEMENT OF THE GLASS SHOULD BE DONE BY
A LICENSED OR QUALIFIED SERVICE PERSON. USE
ONLY REPLACEMENT GLASS PROVIDED BY YOURAUTHORIZED JØTUL DEALER. NEVER USE ANY SUBSTITUTE MATERIALS.

23

138914 Rev. K / 7.27.10

Jøtul GF 370 DV
Operation
Features Overview

The Proflame GTMFS system is a modular remotecontrol system that directs the functions of the Jøtul
GF 370 gas freestanding unit. It is configured to control the on/off operation both manually andthermostatically, with standard and “Smart” thermostat features. It will also control flame modulation, manual flame control, fan on/off and speed andon/off of accent lighting features.

The system is an IPI system (Intermittent Pilot
Ignition) and also has a built in switch which allows
you to keep the pilot lit continuously if desired (CPI
Constant Pilot Ignition). The power is provided to theFCM (Fan Control Module) using 120v electricity andhas a 6volt DC battery back-up for operation during a
power failure.

Remote Control TransmitterThis new remote system has all controls available onits face for reliable, ease of use. It gives room temperature readout, set temperature readout, all function
abilities as well as childproof lockout and low battery
indicator. Icons appear on the screen indicating
which mode of operation you are controlling. The
four button controls are easy to learn and simple tooperate. The remote transmitter is powered by 3-1.5v
AAA batteries.

Remote Control Receiver

The receiver is powered by 4-1.5v AA batteries. This
unit has a manual on/off switch to light the burner if
the remote should become inoperative.

Fan Control Module

The Fan Control Module (FCM) is the electrical heartof the system. It provides power to all components,
120v ac when available, and converts to 6v DC
when it is not. This powers the receiver, making thebatteries in the receiver a backup power source, thus
prolonging the life of the batteries. The FCM sends
power to the fan system and the accent light. Whenno line power is available these features will not
operate.

24

Ignition ModuleThis is the brain of the system. It allows the pilot tobe set up as an IPI or CPI unit. It tells the burner tolight or turn off, and provides the ignitor with theelectricity needed for sparking. All functional commands are routed through this part of the systemand distribute the signal to the appropriate component.

Sit 885 Modulating Valve

This valve has the ability to be stepped down in six
increments between high and low. It can be done
manually or by setting the remote control to the
Smart thermostat modulation mode. Automatic
modulation means that as the room temperatureapproaches the limit set for shut down, the valve
gradually decreases or “steps-down” the fire intensity. Conversely, as room temperature cools, the valve
gradually increases flame intensity. The overall result
is more comfortable even heating, minimizing temperature peaks and valleys.

Pilot Assembly

The pilot contains a pilot hood, igniter, and a sensor
rod. The igniter sends a spark to the pilot hood whichlights the gas. The sensor rod is then engulfed by thepilot flame, flame rectification occurs and the unit
remains lit. If rectification does not occur the mainburner will not light and the pilot will shut down.
WARNING:READ AND UNDERSTAND ALL OPERATING
INSTRUCTIONS BEFORE ATTEMPTING TO OPERATE
THIS APPLIANCE. DO NOT ALLOW ANYONE TO
OPERATE THIS APPLIANCE WHO HAS NOT READ
AND UNDERSTOOD THESE INSTRUCTIONS. KEEP
THE REMOTE CONTROL TRANSMITTER WHERE
CHILDREN CANNOT REACH IT.
WARNING:
SEVERE INJURY. THIS APPLIANCE CAN BE SET TOOPERATE THERMOSTATICALLY. BE AWARE THATTHE STOVE MAY BE VERY HOT EVEN WHEN THE
BURNER IS NOT APPARENTLY OPERATING.
KEEP CHILDREN AWAY FROM THE APPLIANCE.

WARNING:OBSERVE CAUTION NEAR THE GLASS PANEL. THE
GLASS MAY SHATTER IF STRUCK BY AN OBJECT.
ALWAYS HANDLE THE GLASS PANEL WITH CARE.

138914 Rev. K / 7.27.10

Control Functions

CPI (Continuous Pilot Ignition)

Pilot Mode

IPI (Intermittent Pilot Ignition)

In most cases you will want to operate the stove in IPI
mode. This allows the most efficient use of gas, burning the pilot light only when the thermostat calls forthe burner to ignite.

The CPI mode permits functional flexibility within
a wide range of installation characteristics. The pilot
flame remains lit when the burner is off. This is an advantage in those instances when a cold system maybe
difficult to start in IPI mode. The pilot can be run until
the system has warmed sufficiently for IPI operation.
NOTE: THE IGNITOR WILL ALWAYS SPARK WHENEVER
THE PILOT MODE IS SWITCHED TO CPI, REGARDLESS OF
THE POSITION OF THE RECEIVER SWITCH.

Accent Lamp
Dimmer Control

Receiver in “ON”
position

Figure 39. Main Control Panel.

Remote Receiver

The Remote Receiver is powered through the FanControl Module. The Receiver can be set to one of threedifferent positions. See fig. 39.
ON - this is a manual override allowing the burner tofunction without remote control. The ignitor will sparkwithin 3 seconds .

Blue LCD Screen

REMOTE - Permits full function of all components byremote control Transmitter activity.

OFF - Disconnects communication between the transmitter and receiver. Turns off IPI functionality. Turn the
Receiver to “OFF” whenever the stove will not be used
and whenever service is performed.

ON/OFF Key
THERMOSTAT Key

Remote Transmitter

MODE KeyThe Transmitter features a simple button layout andinformative display screen. See fig. 40.

ON / OFF Key - controls Burner, Fan, and Lamp functions.

THERMOSTAT Key - Used to set either Manual or
Thermostatic Control and index through thermostatic
functions.
UP / DOWN Arrow Key - Selects thermostat temperature
range and fan speed.
MODE Key - used to selectthe component to be controlled: Burner, Fan, or Lamp.
DISPLAY - graphically indicates temperature settingsand status of Thermostat,
Burner, Fan, and Lamp.

UP/DOWN Key

Figure 40. Remote transmitter function keys.
Figure 41. Remote transmitter display data.
  









 
 

   

      







25

138914 Rev. K / 7.27.10

Remote Transmitter Controls, cont’d.
Temperature Indication Display
 With the transmitter in the OFF position, press the

Thermostat Key and the Mode Key at the sametime. The display screen will show the current room
temperature cycling between Farenheit and Celsius
indicators each time the keys are pressed simultaneously. See fig. 42.

Figure 42. Room temperature readings

Turn on the Burner Press the ON/OFF Key on the Transmitter.

The display will show all the active icons. At thesame time, the Receiver will activate the Pilot
Ignitor. First the pilot will ignite, followed shortly
by the burner. A single”beep” from the Receiver will
confirm reception of the command.

Figure 43. Burner shut-down

Turn off the Burner Press the ON/OFF Key. The display will show only

the room temperature and icon. At the same time,
the Receiver will deactivate the call for heat and theburner will shut down. Fig. 43. A single”beep” fromthe Receiver will confirm reception of the command.

Remote Burner Control

There are six flame levels available.

 With the system ON, and the burner flame level

Figure 44. Burner OFF.

Figure 45. Flame Level 1.

Figure 46. Flame Level 5.

Figure 47. Flame Level 6.

at maximum, press the Down Arrow Key once toreduce the flame height by one step. Each time the
Down Key is pressed, the flame will step down until
the burner is finally turned off. Fig. 44.

 The Up Arrow Key will increase the flame height

each tim it is pressed. If the U Arrow Key is pressed
while the system is on but the flame is off, theflame will come on in the High position. Figs. 45-47.
A single “beep” will confirm reception of the command.

Room Thermostat (Transmitter Operation)

The Remote Control can operate as a room themostat.
The themostat can be set to a desired temperature tocontrol the comfort level in a room.

Room Temperature To activate this function, press the Thermostat Key,

(Fig. 40.) The display will indicate that the room
thermostat is “ON” and the current Set Temperature
is now displayed. Fig. 48.

 To adjust the Set Temperature, press the Up or

Down Arrow Keys until the desired Set Temperature
is displayed. Fig.49.

26

Set Temperature

Figure 48. Thermostat ON

Figure 49.
Change Set Temperature138914 Rev. K / 7.27.10

SMART Thermostat Function

This function adjusts the flame intensity according to
the difference in the Set Point temperature and theactual room temperature. As the room temperature
gets closer to the Set Point, the Smart Function will
modulate flame intensity down.

 To activate this function, press the Thermostat Key

until the woed “SMART” appears to the right of thethermometer bulb icon. Fig. 50.

Figure 50. Smart Mode

Figure 51. Smart Set Temp.

Figure 52. Fan Mode

Figure 53. Fan Speed

Figure 54. Lamp Control

Figure 55.. Lamp ON

Figure 56. Lock ON

Figure 57. Low Battery

 To adjust the temperature, press the Up or Down
Arrow Keys until the desired Set Temperature isdisplayed. Fig. 51.

Fan Speed Control
 Fan speed can be adjusted through six settings. To

activate this function, press the Mode Key (Fig. 40)
to index to the Fan Control icon. See fig. 52.

 Use the Up/Down Arrow Keys to turn ON, OFF, or
adjust the fan speed. Fig. 53. A single “beep” will
confirm reception of the command.

Accent Lamp Control ( Auxiliary 120V Outlet)
 The auxiliary function controls the Accent Lamp
power. Press the Mode Key to index to the AUX
icon. Figs. 54-55.

 Pressing the Up Arrow Key will turn the Lamp ON.
Lamp brightness can be adjusted by turning thedimmer knob on the stove Control Panel.

 Pressing the Down Arrow Key will turn the Lamp OFF.
Child Safety Lock

This function will lockout the Transmitter to prevent
unsupervised operation.

 To activate the Lock, press the Mode key and UP Key
at the same time. Fig. 56.

 To de-activate the Lock, press the Mode Key and UP
Key at the same time.

Low Battery Detection

The life-span of the batteries depends on various
factors; battery quality, the frequency of ignition calls,
the frequency of changes to Set Points, etc.

 When Transmitter batteries are low, the Battery

icon will be displayed before all battery power islost. The icon will disappear when new batteries
are installed.

 When Receiver batteries are low, no “beep” will

be emitted from the Receiver when it receives an
On/Off command from the Transmitter. This is analert for a low battery condition in the Receiver.
When the batteries are replaced, the “beep” will

be emitted from the Receiver when the ON/OFF
Key is pressed. See Battery Replacement under the
Maintenance section of this manual.

Manual By-Pass of the Remote System

When battery power is low or depleted, the burner
can still be operated manually by sliding the Receiverswitch to the ON position. It will immediately ignite
in the High position.

In the event of a power failure, flame modulation,
themostatic control, fan and lamp functions will be
unavailable. It is therefore advisable to keep a supply
of good quality batteries on hand.

27138914 Rev. K / 7.27.10


  



 



  

    






­ 
­

 

   



     
  

Figure 58. Wiring schematic, SIT Proflame 885 Burner Control System

Technical Data

Fan Control Module
Supply voltage/frequency:
120V, 60 Hz
Ambient temp. ratings:
32 to 140° F
Three wire bus: -Two wires provide DC voltage to			the Receiver		- One wire gives uni-directional			signal from the Receiver
Output voltage/frequency/current: 120V / 60 Hz / 5 A
Auxiliary switched output:
120V / 60 Hz / 2 A
Fan speed output:		
120V / 60 Hz / 1 A
Remote Control Transmitter
Supply voltage:
4.5 V (three 1.5V AAA batteries)
Ambient temp. rating:		
32 to 122° F
Radio frequency:		
315 MHz
Receiver:Supply voltage
6.0 V (four 1.5 AA batteries)
Ambient temp. rating:		
32 to 140° F
Radio frequency:		
315 MHz

28









Figure 59. Wiring Diagram - GF 370 DV Fan
CAUTION: LABEL ALL WIRES PRIOR TO DISCONNECTION WHEN SERVICING THE CONTROLS. WIRING ERRORS CAN CAUSE IMPROPER AND DANGEROUS OPERATION. ALWAYS VERIFY PROPEROPERATION AFTER SERVICING THE APPLIANCE.
ATTENTION: AU MOMENT DE L’ENTRETIENDES
COMMANDES, ÉTIQUETEZ TOUS LES FILS AVANT
LE DÉBRANCHEMENT. DES ERREURS DE CÂBLAGE
PEUVENT ENTRAÎUN FONCTIONNEMENT INADÉQUAT ET DANGEREUX.

138914 Rev. K / 7.27.10

This page is intentionally blank.

29138914 Rev. K / 7.27.10

MaintenanceThis appliance and its venting system should be
inspected before use and at least annually by a qualified service technician.
WARNING!
THE IGNITION SYSTEM OF THIS APPLIANCECARRIES LIVE VOLTAGE. ALWAYS TURN “OFF “
THE MAIN GAS SUPPLY AND DISCONNECT THE
POWER SOURCE BEFORE PERFORMING ANY
MAINTENANCE PROCEDURE.
TURN “OFF “ THE MAIN GAS SUPPLY AND DISCONNECT THE POWER SUPPLY TO THE APPLIANCE BEFORE REPLACING BATTERIES.

Annual Cleaning
Vent System

The entire vent system should be inspected andcleaned every year. If the intake and exhaust venting
is disassembled for any reason, it should be reassembled and sealed according to the vent manufacturer’s
instructions provided at the initial installation.

Burner and Log Set

Periodically inspect the firebox and valve compartment to BE CERTAIN THAT THE FLOW OF COMBUSTION
AND VENTILATION AIR IS UNOBSTRUCTED.
The firebox should be vacuumed at least annually to remove any surface build up. Use a soft brushattachment and handle the logs carefully as they are
fragile.

Glass Care

Clean the glass as necessary. Wipe the surface witha clean, dampened, soft cloth. Follow with a dry, soft
towel. Take care not to scratch the glass surface.
WARNING: DO NOT USE ABRASIVE CLEANERS
ON THE GLASS. NEVER CLEAN THE GLASS WHEN
IT IS HOT.

Gasket Inspection

It is important that the glass gasket be inspected atleast annually. Examine the ribbon gasket for signs ofdeterioration and make sure the gasket has a positive
seal. Replace the gasket if necessary.

30

FOR REPLACEMENT, USE ONLY JØTUL
CERAMIC GLASS PANEL KIT 156817. DO NOTUSE ANY OTHER TYPE OF GLASS WITH THISAPPLIANCE.

Glass Panel or Gasket Replacement

1. Use the 4 mm hex key to remove the four socket
screws that attach the Glass Frame to the firebox.
Remove the lower screws first and be sure toadequately support the frame against the firebox
while you remove the upper screws.

2. Lay the assembly upside down on a flat surface,protecting the frame from scratches using a blanket or towel.
3. The glass panel is held in place by four retainer
tabs. Use a screwdriver to carefully pry these up
off the edge of the glass retaining walls. If thetabs break off, use the Tinnerman clips suppliedwith the replacement glass kit to secure the glass
panel within the frame.
4. Remove the old gasket material.

5. Beginning at the midpoint of the upper edge, apply the new gasket around the glass panel, withthe adhesive side inside and the thicker portion
on the outside. DO NOT STRETCH THE GASKET
MATERIAL. Trim off any excess, leaving a 1/2” overlap as shown in fig. 60.
6. Lay the glass panel within the glass frame andpress the tabs back down or press the clips inplace as shown in fig. 61.

Figure 60.
Gasket application,
PN 129124

138914 Rev. K / 7.27.10

Figure 61.
156817 Glass
Replacement
Kit includes
gasket and spareretainer clips.

Initializing the Remote Control

Each time you replace the batteries, you will need toinitialize communication between the Receiver andthe Transmitter.
1. Place the slider switch in the REMOTE position.

2. Insert the end of a paper clip into the hole marked
PRG on the Receiver cover. The Receiver will “beep”
three (3) times to indicate that it is ready to synchronize with the Transmitter.
3. Install 3 AAA batteries in the Transmitter bay andpush the ON button. The Receiver will “beep” fourtimes to indicate the Transmitter’s command isaccepted and sets to the particular code of that
Transmitter. The system is now initialized.

Battery Replacement

Battery life depends on many variables; the quality ofthe batteries, frequency of remote use, and mode ofpilot operation. Keep a supply of good quality batteries on hand to be assured of functional continuity inthe event of a power failure.

The Remote Transmitter batteries are easily
accessed through the tabbed cover plate. Be sure toorient the batteries for correct polarity as indicated in
the battery compartment.
WARNING!
ALWAYS SHUT OFF THE GAS SUPPLY ANDDISCONNECT THE POWER CORD FROM HOUSE
CURRENT BEFORE REPLACING BATTERIES.

Receiver Battery Replacement

1. Push the slider switch into the OFF position. Remove the Receiver cover plate screws and pry thecover plate with slider switch off of the battery
box. See fig. 62.
2. Install 4 AA batteries into the receiver bay. Notethe polarity of the batteries and insert into thebattery bay as indicated on the bay cover (+/-).

Figure 62. Access Receiver batteries.

Accent Lamp Replacement

Handle the replacement bulb with gloves. Skin oils
will cause the bulb to fail prematurely.
1. Remove the glass frame. See fig. 18.

2. Remove the two retainer screws with a short phillips screwdriver. Pull the socket out of the housing.
3. Plug the new bulb into the socket and re-install
the assembly into the lamp housing.

4. Replace the glass frame using the 4 mm hex key
and socket head screws previously removed.
PN 222943 Bulb, 130V / 50W

3. With the switch still in the OFF position, align theslider switch with the switch stem and snap thecover plate back onto the battery box.
4. Replace the Receiver cover plate screws.

Figure 63. Accent Lamp Replacement.

31

138914 Rev. K / 7.27.10









 

































































Figure 64.
Firebox Part Identification.
No.
1
2
3
4
5
6
7
8
9
10
12
13
14
15
16
17
18
19
20

32

Part Number
9911		
9962
11791711796711796811797811803912000412911822258022258892
22258992
22273592
15683322294322297422298092
222981
222982

Description
Bolt, Hex Cap, M6x45, DIN 933, Class 8.8, Blk
Bolt, Hex Cap M6x10 DIN 933 8.8 Ser Flange Blk
Screw, HWH SMA 8 x 1/2 SL Blk Oxide
Screw, Pan Head #7 x 3/8 PH SMA Zinc
Nut, M6 Serrated Flange plain
Screw, Button Head Socket M6X10 Blk
Spacer, .375 O.D. x 1.188
Washer,Fender M6 DIN 9021B Zinc
Gasket, Starter
Firebox Weldment, GF 370
Baffle, Firebox, GF 370, MB
Glass Frame, Side, Inner, GF 370, MB
Glass Shade, Side, GF 370, MB
Replacement Front Glass & Gasket, GF 370
Light Bulb, 130 Volt, 50 Watt
Glass, Ceramic, Light Fixture, GF 370
Restrictor, Rod & Washer Assy, GF 370, MB
Delay Door, GF 370
Restrictor Plate, GF 370










No. Part Number Description
2122298392
Simpson DV Starter Collar, GF 370, MB
22222988Light Box, Inner
23
22298992
Light Box, Outer, MB
24223202Intake Manifold, GF 370
2522320592
Burner Skirt, Rear, GF 370, MB
26
156834
Replacement Inner Side Glass & Gasket, GF 370
2722324392
Panel Retainer, GF 370
28223295Gasket, Intake Manifold, GF 370
29118201Screw, Button Head Socket, M6 X 16, Blk
30
22259292
Glass Frame, Curved, GF 370, MB
31
156824
Replacement Light Socket Ass’y, GF 370
32222977
Gasket, Light Kit
33
222993Gasket, Relief Door, GF 370
34223241
Gasket, Exhaust Restrictor, GF 370
35118090Screw, HWH SMA 8 x 5/8 SL Zinc
36
22321992
Shroud, Rear, GF 370, MB
37
22328292
Firebox Cover, GF 370, MB
38* 223224
Skamol, Rear Panel		
39* 223235
Skamol, Side Panel, 2						* not illustrated

138914 Rev. K / 7.27.10






















































































No.
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
16
17
18
19
20

Part Number
9962
99115
10447092
10431992
10448892
10453692
1180191179471179681179769906
117978118095120004
22266422272922299592
22299822299922320792

Figure 65.
External parts identification












Description
Bolt, Hex Cap M6x10 DIN 933 8.8 Ser Flange Blk
Bolt, Hex Head M8 x 12 Blk
Top Plate, MB - GF 370
Pedestal Base, MB - GF 370
Pedestal Side, MB - GF 370
Cover, Access, MB - GF 370
Bolt, Hex Hd Serr Flange M6 x 25 Blk
Washer, Flat M6 -.062 DIN 125A Plain
Nut, M6 Serrated Flange plain
Screw, Flat Head Phillips M6 X 12 M/S Blk
Bolt, Hex Cap, M6x30, DIN 933, Class 8.8, Blk
Screw, Button Head Socket M6 x 10 Blk
Screw, HWH, SMA, #8 x 1”, SL, Zinc
Washer,Fender M6 DIN 9021B Zinc
Protection Cap, M8 Hex, Black
Door Handle, Plated, GF 370
Top Grill, GF 370, MB
Bracket, Firebox Mount, GF 370
Bracket, Side Support, GF 370
Bracket, Door Catch, GF 370, MB

No.
21
22
23
24
25
26
27
28
29
30
31
32
33
34
35
36
37
38
39

Part Number Description
156843Lower Door Hinge Asy. GF 370, MB
156835
Replacement Outer Side Glass, GF 370
22321692
Bracket, Blower Mount, GF 370, MB
22321892
Bracket, Outer Glass Kit, Lower, GF 370, MB
223220
Plate, Centering, GF 370
223227
Blower, Axial, 40 CFM, 120 V
22323292
Hinge, Door, MB
223236
Label, Caution,
99625
Bolt, Hex Head Serr Flange M6x16 8.8 Blk
223290Latch, Magnetic
156837
Replacement Outer Side Glass Clip Ass’y.
22328592
Bracket, Handle, MB
10446392
Door, MB10446492
Side Plate, Left, MB
10446592
Side Plate, Right, MB
118055
Kepnut, M4, Ext. Tooth Lockwasher, Stl, Zinc
22383292
Rear Cover, MB
224201
Gas Line Retainer
118236Screw, M6 x 20

33

34

































































































138914 Rev. K / 7.27.10

Figure 66. Spud Assembly parts identification

138914 Rev. K / 7.27.10
No.
1
2
3
4
5
6
7
8
9
10
10
11
12
13
14
15
16
17
18
19
20
21
22
22
23
24
24
25
26
27
28
29
30
31
32
33
34
35
36
37
38
39*
40
41

Part Number Description
118214Screw, #8 X 3/8”, Taptite, SLHWH, SZPL
117917
Screw, HWH SMA 8 x 1/2 SL Blk Oxide
117967
Screw, Pan Head #7 x 3/8 PH SMA Zinc
117968Nut, M6 Serrated Flange plain
117975
Nut,Wing M6 Zinc
118023
Washer, Fender .250 x 2.250
9962
Bolt, Hex Cap M6x10 DIN 933 8.8 Ser Flange Blk
156813
Wire Harness, Replacement - IPI / GF 370
223235Flex tube w/connectors (3/8in O.D. x 34in)
129130Orifice, #38 / NG
045025
Orifice, #52 / LP
223230Gasket, Spud Plate, GF 370
129670Gasket, Pilot Assembly
156836
Replacement 1.5’ Power Cord Ass’y, GF 370
120517
Switch, Rocker, SPST, Black, Plain
220709Knob, Rheostat Control
220734
Gasket, 2.25in OD x .125
221390Primary Air Shutter Asby
222292
Elbow, 90 deg, Brass 3/8 NTP X 3/8” Dia Tube
223204
Pilot Air Deflector, GF 370
222926
Proflame GTMFS Transmitter
222910Spacer, Pilot, GF 370
222922
Proflame Valve w/Stepper Motor, NG only
222952
Proflame Valve w/Stepper Motor, LP only
222924
Proflame IPI Ignition Board
156802
Replacement Proflame Pilot, NG
156803Replacement Proflame Pilot, LP
157026
Proflame Fan Control Module, Replacement222928
Proflame S Receiver
222911
Gasket, Pilot Spacer, GF 370
222941
Elbow, Brass, Street, 90 deg, 3/8 NTP
222987
Intake Restrictor, GF 370
223201
Handle, Primary Air, GF 370
222280Gasket, Drop In Orifice Holder
223246
Control Face Plate, Silkscreened, GF 370
156812Burner Assembly, Complete / GF 370
223231
Orifice Holder, Drop In Assembly, GF 370
223233
Spud Plate Weldment, GF 370
156823Replacement Light Dimmer, GF 370
223244
Bracket, IPI Ignition Board
156825
Replacement Spud Ass’y, GF 370, NG, 30%TD
156838Replacement Spud Ass’y, GF 370, LP, 30%TD
222058
Pilot Orifice, Pop-top #62 / NG
129473
Pilot Orifice, Pop-top #35 / LP
224132
Spacer, Orifice Holder
224201
Gas Line Retainer

Use only genuine Jøtul Replacement Parts
available from your local Authorized Jøtul
Dealer or by contacting:Jøtul North America
55 Hutcherson Dr.
Gorham, ME 04038
207 591-6601*Not illustrated

35

138914 Rev. K / 7.27.10

Appendix A
Mobile Home Installation

The Jøtul GF 370 DV can be installed for use in a
mobile home in the U.S. and Canada provided:

Correct Flame Pictures

1. The stove must be secured to the floor of themobile home. There is a hole for this purpose,
located in the pedestal base, through which alag screw or other appropriate fastener should
be secured to the floor. See Fig. 1, page 3.

2. The stove is installed in accordance with Title 24
CFR, Part 3280- Manufactured Home Construction and Safety Standard, in the U.S. Comply
with CSA Z240.4, Gas Equipped Recreational
Vehicles and Mobile Housing, in Canada.
3. Always contact your local officials about installation restrictions and requirements in yourarea.

THIS APPLIANCE MAY BE INSTALLED AS AN OEM
INSTALLATION IN A MANUFACTURED (MOBILE)
HOME AND MUST BE INSTALLED IN ACCORDANCEWITH THE MANUFACTURER’S INSTRUCTIONS AND
THE MANUFACTURED HOME CONSTRUCTION
AND SAFETY STANDARD, TITLE 24 CFR, PART
3280, STANDARD FOR MANUFACTURED HOME
INSTALLATION, ANSI/NCBCS A255.1 OR STANDARD
FOR CANADA, CSA Z240.4. THIS APPLIANCE IS ONLYFOR USE WITH THE TYPE OF GAS THAT IS INDICATEDON THE STOVE’S RATING PLATE. THIS APPLIANCE
MAY BE INSTALLED IN AN AFTERMARKETPERMANENTLY LOCATED, MANUFACTURED(MOBILE) HOME, WHERE NOT PROHIBITED BY
LOCAL CODE.

Figure 67. Wishing Rock flame picture. KEEP EMBERSTONES OFF PILOT CARRY-OVER PORTS.



CET APPAREIL PEUT ETRE INSTALLE DANS UN
MAISON PREFABRIQUEE (MOBILE) DEJA INSTALLEEA DEMEURE SI LES REGLEMENTS LOCAUX LEPERMETTENT.
CET APPAREIL DOIT ETRE UTILISE UNIQUEMENTAVEC LES TYPES DE GAS INDIQUES SUR LA PLAQUE
SIGNALETIQUE. NE PAS L’UTILISER AVEC D’AUTRESGAS SAUF SI UN KITDE CONVERSION CERTIFIE ESTINSTALLE.

Figure 68. Starfire Glass flame picture.

36

138914 Rev. K / 7.27.10

37138914 Rev. K / 7.27.10

Jøtul Gas Product
Limited WarrantyThis warranty policy applies to gas products identified by
Jøtul, Scan, and Atra trade names, as set forth below.

A. Cast Iron, Steel Doors, Surround Components, Firebox:

Jøtul North America Inc. (JØTUL) warrants, to the originalretail purchaser, that those components of the Jøtul, Scan,or Atra Gas Stove or Fireplace specified above will be freeof defects in material and workmanship for a period offive (5) years from the date of purchase. This warranty is
subject to the terms, exclusions and limitations set forth in
the following text.
B. Burner, Burner Treatments, Firebox Panels:JØTUL warrants, to the original retail purchaser, thatthose components of the Jøtul, Scan, or Atra Gas Stove or
Fireplace specified above will be free of defects in material
and workmanship for a period of two (2) years from thedate of purchase. This warranty is subject to the terms,
exclusions, and limitations set forth in the following text
C. Gas & Electrical Components (controls, plumbing, valve,
blower):JØTUL warrants, to the original retail purchaser, thatthose components of the Jøtul, Scan, or Atra Gas Stove or
Fireplace specified above will be free of defects in material
and workmanship for a period of one (1) year from thedate of purchase. This warranty is subject to the terms,
exclusions, and limitations set forth in the following text.
JØTUL will repair or replace (including parts & labor), at its option, anyof the above components determined by JØTUL to be covered by thiswarranty. You must, at your own expense, arrange to deliver or ship thecomponent to an authorized Jøtul, Scan, or Atra dealer and arrange for
pickup or delivery of the component after repairs have been made. If,
upon inspection, JØTUL determines that the component is covered bythis warranty, the repair or replacement will be made as set forth above.
This warranty is not transferable and is extended only to, and is solely forthe benefit of, the original retail purchaser of the Jøtul, Scan, or Atra Gas
Stove or Fireplace. This paragraph sets forth the sole remedy available
under this warranty in the event of any defect in the Jøtul, Scan, or Atra
Gas Stove or Fireplace.
The warranty period for any replaced component will be the remaining
unexpired portion of the warranty period for the original component.
Please retain your dated sales receipt in your records as proof of purchase.
EXCLUSIONS AND LIMITATIONSNOTICE: This warranty is void if installation or service is performedby someone other than an authorized installer, service agency or gas
supplier, or if installation is not in conformance with the installation andoperating instructions contained in this owner’s manual or local and/or national fire and building regulations. A listing of local authorized
installers, service agencies and gas suppliers can be obtained from the
National Fireplace Institute at http://www.nficertified.org/.
This warranty does not cover the following:
1) Repair or replacement of parts that are subject to normal wear andtear during the warranty period or to parts that may require replacement
in connection with normal maintenance. These parts include gaskets andglass (except to the extent such parts suffer damage from thermal stress).
2) Damage due to incorrect installations not in conformance with the38

installation instructions contained in this owner’s manual or local and/or
national fire and building regulations.
3) Damage due to service performed by an installer, service agency orgas supplier, unless otherwise agreed to in writing by JØTUL.
4) Labor or other costs associated with the repair of gas controls,
plumbing, burners, log set, or sheet metal firebox beyond the warranty
period.
5) Damage caused by unauthorized modification, use or repair.
6) Damage to enameled surfaces caused by improper operation or
misuse, including use that is not in conformance with the operating
instructions contained in this owner’s manual. Such damage cantypically be identified by bubbling, cracking, or discoloration of theenamel finish.
7) Costs incurred by travel time and/or loss of service.
8) Damage incurred while the Jøtul, Scan, or Atra Gas Stove or Fireplaceis in transit.
IN NO EVENT SHALL JØTUL, ITS PARENT COMPANY, SHAREHOLDERS,AFFILIATES, OFFICERS, EMPLOYEES, AGENTS OR REPRESENTATIVESBE LIABLE OR RESPONSIBLE TO YOU FOR ANY SPECIAL, INDIRECT,INCIDENTAL, CONSEQUENTIAL, PUNITIVE OR OTHER SIMILAR DAMAGES,INCLUDING, BUT NOT LIMITED TO, LOST PROFITS, LOST SALES, INJURYTO PERSON OR PROPERTY, OR DAMAGES TO A STRUCTURE OR ITSCONTENTS, ARISING UNDER ANY THEORY OF LAW WHATSOEVER.
ALL IMPLIED WARRANTIES, INCLUDING THE IMPLIED WARRANTIESOF MERCHANTABILITY AND FITNESS FOR A PARTICULAR PURPOSE,
OR OTHERWISE, ARE LIMITED IN DURATION TO THE LENGTH OF THISWRITTEN WARRANTY. EXCEPT AS EXPRESSLY SET FORTH HEREIN, JØTUL
MAKES NO ORAL, WRITTEN OR OTHER WARRANTY WITH RESPECT TO
JØTUL, SCAN OR ATRA GAS STOVES OR FIREPLACES.
Some states do not allow the exclusion or limitation of incidental
or consequential damages, or limitations on the length of implied
warranties. Therefore, the above exclusions or limitations may not apply
to you. This warranty gives you specific legal rights, and you may haveother rights, which vary from state to state.
JØTUL reserves the right to discontinue, modify or change the materials
used to produce the Jøtul, Scan, or Atra Gas Stove or Fireplace. JØTUL
shall have the right to replace any defective component with substitutecomponents determined by JØTUL to be of substantially equal quality
and price.
The dollar value of JØTUL’s liability for breach of this warranty shall belimited exclusively to the cost of furnishing a replacement component.
JØTUL shall not in any event be liable for the cost of labor expended
by others in connection with any defective component. Any costs or
expenses beyond those expressly assumed by JØTUL under the terms ofthis warranty shall be the sole responsibility of the owner(s) of the Jøtul,Scan, or Atra Gas Stove or Fireplace.
No dealer, distributor, or other person is authorized to modify, augment,
or extend this limited warranty on behalf of JØTUL. NO MODIFICATION
OR CHANGE TO THIS WARRANTY WILL BE EFFECTIVE UNLESS IT IS MADE
IN A WRITTEN DOCUMENT MANUALLY SIGNED BY AN AUTHORIZEDOFFICER OF JØTUL.
An authorized installer may have been provided with certain
information related particularly to the Jøtul, Scan, or Atra Gas Stove or
Fireplace; however, no authorized installer or other person who may
service the appliance is an agent of JØTUL. No inference should be madethat JØTUL has tested, certified, or otherwise pronounced any person as
qualified to install or service the appliance. JØTUL shall not be liable orotherwise responsible for any error or omission by a person installing orservicing a Jøtul, Scan, or Atra Gas Stove or Fireplace.
If you believe your Jøtul, Scan, or Atra Gas Stove or Fireplace is defective,
you should contact your nearest authorized Jøtul, Scan, or Atra
dealer, who will process a warranty claim. IN ORDER TO QUALIFY FOR
WARRANTY COVERAGE, JØTUL MUST RECEIVE NOTICE OF A POSSIBLE
DEFECT WITHIN SIXTY (60) DAYS OF THE DATE THE DEFECT IS FIRSTDISCOVERED, OR REASONABLY COULD HAVE BEEN DISCOVERED.
This warranty is given by Jøtul North America, Inc.,
55 Hutcherson Drive, Gorham, Maine 04038 USA

LIGHTING INSTRUCTIONS

138914 Rev. K / 7.27.10

FOR YOUR SAFETY, READ BEFORE LIGHTING.
WARNING:IF YOU DO NOT FOLLOW THESE INSTRUCTIONS EXACTLY, A FIRE OR EXPLOSION
MAY RESULT CAUSING PROPERTY DAMAGE, PERSONAL INJURY, OR LOSS OF LIFE.
A. This appliance is equipped with an ignition
device which automatically lights the pilot.
Do not try to light the pilot by hand.

B. BEFORE LIGHTING, smell all around the appliance area for gas. Be sure to smell next to thefloor because some gas is heavier than air andwill settle to the floor.
WHAT TO DO IF YOU SMELL GAS:
• Extinguish any open flame.
• Open windows.
• Do not light any appliance.
• Do not touch any electrical switches.
• Do not use any phone in your building.
• Immediately call your gas supplier from aneighbor’s phone.

• If your gas supplier cannot be reached, call thefire department.
C. Use only your hand to push in or turn thegas control knob. Never use tools. If the knob
will not push in or turn by hand, do not try
to repair it. Call a qualified technician. Forceor attempted repair may result in a fire or
explosion.

D. Do not use this appliance if any part has been
under water. Immediately call a qualified service technician to inspect the appliance and to
replace any part of the control system and any
gas control which has been under water.

LIGHTING INSTRUCTIONS
1. STOP! Read the safety information above.
2. Set the thermostat to the lowest setting.

3. Set the Mode Control Switch to the “OFF” position.
4. This appliance is equipped with an ignition device
which automatically lights the pilot.
Do not try to light the pilot by hand.

7. Set the Mode Control Switch to the “REMOTE” position.

PILOT LIGHT ASSEMBLYREMOTE RECEIVER
MODE CONTROL SWITCH

5. Wait five (5) minutes to clear out any gas. Then,smell for gas, including near the floor. If you smellgas, STOP! Follow “B” in the safety information
above on this label. If you do not smell gas, go to
the next step.

8. Set the thermostat to the desired setting to lightthe burner.

9. If the appliance will not operate, follow the instructions” To Turn Off Gas To Appliance”, and callyour service technician or gas supplier.

6. Set the Mode Control Switch to the “ON” position.
The pilot will light.

TO TURN OFF GAS TO THE APPLIANCE:
1. Set the thermostat to the lowest setting.

2. Turn off all electrical power to the appliance if
service is to be performed.

3. Set the Mode Control Switch to the “OFF” position.
4. Close control access door.

39

138914 Rev. K / 7.27.10

July 2010
138914-K

This appliance must be installed in conformance with local and national building regulations. Before
beginning the installation, it is important that the these instructions be carefully read and understood.
Jøtul maintains a policy of continual product development. Consequently, products may differ in specification, color or type of accessories from those illustrated or described in various publications.
Jøtul vise sans cesse a ameliorer ses produits. C’est pourquoi, il se reserve le droit de modifier les specifications, couleurs etequipement sans avis prelable.

Jøtul AS
P.O. Box 1411
N-1602 Fredrikstad
NorwayJøtul North America
55 Hutcherson Dr.
Gorham, ME 04038-2634

40