564 HO GS
Fireplace
Tested and Listed by

ANSI Z21.88



Built-In Direct Vent FireplaceNatural Gas or Propane

Residential or Mobile HomeWARNING:

If the information in these instructions is not followed exactly, a fire or
explosion may result causing property damage, personal injury or loss of life.
- Do not store or use gasoline or other flammable vapors and liquids in the vicinity of this or
any other appliance.
WHAT TO DO IF YOU SMELL GAS• Do not try to light any appliance.
• Do not touch any electrical switch; do not use any phone in your building.
• Immediately call gas supplier from a neighbor's phone. Follow the gas supplier's
instructions.
• If you cannot reach your gas supplier, call the fire department.
- Installation and service must be performed by a qualified installer, service agency or the gas
supplier.
This appliance may be installed in
an aftermarket permanently
located, manufactured home (USA
only) or mobile home, where notprohibited by local codes.
This appliance is only for use
with the type(s) of gas indicatedon the rating plate. A conversion
kit is supplied with the appliance.

Installation Manual
Installer:

After installation give this manual to the homeowner and explain operation of this heater.
 Copyright 2011, T.I.
$10.00100-01263_000
4110505

www.travisproducts.com

4800 Harbour Pointe Blvd. SW
Mukilteo, WA 98275

Certified for USA and Canada© Travis Industries

4110505

CAUTION: Hot while in operation. Do Not Touch. Severe burns may result. Keep children,
clothing, furniture, gasoline and other liquids having flammable vapors away. Do not operate
this appliance with glass removed, cracked or broken. Replacement of the panel(s) should bedone by a licensed or qualified service person.
0962

National Fireplace Institute

VENTED GAS FIREPLACE HEATER - NOT FOR USE WITH SOLID FUEL

This manual has been submitted to the
Massachusetts Board of State Examiners of
Plumbers and Gas Fitters.
L.P.
35,0007,500

N.G.
35,00010,400

Minimum Inlet Pressure (inches W.C.)
Maximum Inlet Pressure (inches W.C.)
Manifold Pressure on “HI” (inches W.C.)

11”
13”
10”

L.P.

Manufacture
Date:

Jan.
Feb.
Mar.

2011
2012
2013

Electrical Rating: 115V., 60 Hz, 1.5 Amps

Jun.

May

Apr.

Sep.

Aug.

Jul.

Dec.

Nov.

Oct.

www.travisproducts.com

5.5”
7”
3.5”

N.G.

56” (1423 mm)
0.5” (13 mm)
48.75” (1239 mm)

This appliance is equipped for use only at altitudes 0-2000 feet (0-610m) in the USA. In Canada, 0-4500 feet (0-1370m).
For altitudes above 2000 feet, the vent configuration, orifice, or combination of both may need to be changed.
See the owner’s manual for information on making these changes.

For natural gas when equipped with the following drill size orifice: DMS 50 Front - DMS 44 Back
For propane when equipped with the following drill size orifice: 1.10mm Front - DMS 55 Back

Input Rate on “HI” (BTU/Hr)
Input Rate on “LO” (BTU/Hr)

Listing Details

Base of Fireplace to Enclosure Top
Sides to Enclosure
Base of Fireplace to a 12” Mantel*(*See manual for other mantel depths)

This manual details the installation requirements forthe 564 HO GS fireplace. For operating andmaintenance instructions, refer to the 564 HO GS
Owner's Manual (part # 100-01264).

12” (305 mm)
0” (0 mm)0” (0 mm)

Overview

Tested to: ANSI Z21.88-2009/CSA 2.33-2009 “Vented Gas Fireplace Heaters”, CGA 2.17-M91, UL 307b-2006 “Gas Burning Heating
Appliances for Manufactured Homes”, and CSA P.4.1-09.
This appliance must be installed in accordance with local codes, if any; if none, follow the National Fuel Gas Code, ANSI
Z223.1/NFPA 54, or Natural Gas and Propane Installation Codes, CSA B149.1.
This appliance must be installed in accordance with the current Standard CAN/CSA Z240 MH, Mobile Housing, in Canada or with
the Manufactured Home Constructions and Safety Standard, Title 24 CFR, Part 3280, in the United States, or when such astandard is not applicable, ANSI/NCSBCS A225.1/NFPA 501A, Manufactured Home Installation Standard.
This vented gas fireplace heater is equipped at the factory for use with natural gas. If conversion to propane (LP) is desired, theoptional factory conversion kit must be used.
This appliance is only for use with the type of gas indicated on the rating plate and may be installed in an aftermarket,
permanently located, manufactured home (USA only) where not prohibited by local codes. See owner’s manual for details. Thisappliance is not convertible for use with other gases, unless a certified kit is used.
This vented gas fireplace heater is not for use with air filters.
Keep burner and control compartment clean. See installation and operating instructions accompanying appliance.
This appliance must be properly connected to a venting system in accordance with the manufacturer’s installation instructions.
Use only approved coaxial direct vent system to vent this appliance to the exterior. See owner’s manual for approved brands ofventing.
WARNING: Improper installation, adjustment, alteration, service or maintenance can cause injury or property damage. Refer tothe owner’s information manual provided with this appliance. For assistance or additional information consult a qualified
installer, service agency or the gas supplier.

Report No. B100307498PRT-001
Control No. 4000515

This appliance was listed by Intertek Test Labs to
ANSI Z21.88. The listing label is attached to theappliance near the gas control valve. A copy isshown to the right.

MINIMUM CLEARANCES TO COMBUSTIBLES

Massachusetts Approval

Fireplace to Adjacent Wall
Wood Floor Beneath Fireplace
Back to Enclosure

2
Introduction

100-01263_000

Table of Contents
Restrictor Position ........................................ 20
Exhaust Restrictor Adjustment ..................... 20
Intake Restrictor Adjustment ........................ 21
Diffuser Plate Adjustment............................. 22

Overview ........................................................... 2
Listing Details ................................................... 2
Installation Options.......................................... 6
Heating Specifications..................................... 6
Dimensions ....................................................... 6
Packing List ...................................................... 7
Additional Items Required............................... 7
Installation Overview ....................................... 7
Recommended Installation Procedure .......... 8
Massachusetts Requirements ........................ 9
Requirements for the Commonwealth of
Massachusetts ................................................ 9
MANUFACTURER REQUIREMENTS ........... 93

Vent Configurations with Horizontal
Termination (EmberFyre Burner only) ......... 23
Vent Configurations with Vertical
Termination (EmberFyre Burner only) ......... 24
Vent Configurations with Horizontal
Termination (Dancing/DiamondFyre)........... 25
Vent Configurations with Vertical
Termination (Dancing/DiamondFyre)........... 26
Hearth Requirements .................................... 28
Facing Requirements .................................... 29
Drywall Installation ....................................... 29
Facing Overview........................................... 30
Optional Faceplates – Sizing Chart.............. 30
Thin Facing Installation (tile, marble, or othernon-combustible under 1" (25mm) thick) ..... 31
Thin Facing Installation (tile, marble, under 1"(25mm) thick) — Side View.......................... 32
Thick Facing Installation (stone, brick, or othernon-combustible over 1" (25mm) thick) ....... 33
Thick Facing with Fireplace Xtrordinair (FPX)
Arched Faces ............................................... 34
Thick Facing Installation — Side View ......... 35

Fireplace Placement Requirements ............. 10
Clearances ................................................... 10
Raised Fireplaces ......................................... 10
Minimum Framing Dimensions ..................... 11
Nailing Brackets............................................ 12
Corner Installations....................................... 13
Gas Line Requirements ................................. 14
Fuel ............................................................... 14
Gas Line Connection .................................... 14
Gas Inlet Pressure ........................................ 14
Gas Line Location......................................... 15

Mantel Requirements .................................... 36

Electrical Connection (required) .................. 16

Combustible Mantels .................................... 36

Optional Wall Switch or Thermostat
Installation ...................................................... 17

Steps for Finalizing the Installation ............. 37

Parallel Connection

Air Shutter Adjustment ................................. 38

Series Connection 17

Glass Frame Removal and Installation ........ 39

Vent Requirements ........................................ 18

Glass Frame Removal and Installation(continued) ..................................................... 40

Vent Clearances ........................................... 18
Altitude Considerations................................. 18
Approved Vent .............................................. 19
Vent Installation ............................................ 19

LP Conversion Instructions .......................... 41
Installation .................................................. 41
Index............................................................. 58

Approved Vent Configurations ..................... 20© Travis Industries

4110505

100-01263_000

4Safety Precautions
Safety Warnings:


Failure to follow all of the requirements may result in property damage, bodily injury, or even death.

This unit must be installed by a qualified installer to prevent the possibility of an explosion.

This appliance must be installed in accordance with all local codes, if any; if not, in U.S.A. follow ANSI
Z223.1 and NFPA 54(88), in Canada follow CSA B149.1.

A manufactured home (USA only) or mobile home OEM installation must conform with the
Manufactured Home Construction and Safety Standard, Title 24 CFR, Part 3280, or, when such astandard is not applicable, the Standard for Manufactured Home Installations, ANSI/NCSBCS
A225.1, or Standard for Gas Equipped Recreational Vehicles and Mobile Housing, CSA Z240.4. Thisappliance may be installed in Manufactured Housing only after the home is site located.

All exhaust gases must be vented outside the structure of the living-area. Combustion air is drawn
from outside the living-area structure. The venting must not be connected to a chimney flue serving aseparate solid-fuel burning appliance.

Notify your insurance company before hooking up this fireplace.



The room heater should be inspected before use and at least annually by a qualified service person.
More frequent cleaning may be required due to excessive lint from carpeting, bedding material, etc.



The instructions in this manual must be strictly adhered to. Do not use makeshift methods orcompromise in the installation. Improper installation will void the warranty and safety listing.

This heater is approved for use with natural gas (NG) or propane (LP). Burning the incorrect fuel willvoid the warranty and safety listing and may cause an extreme safety hazard. Direct questions about
the type of fuel used to your dealer.



Contact your local building officials to obtain a permit and information on any installation restrictions
or inspection requirements in your area.



If the flame becomes sooty, dark orange in color, or extremely tall, do not operate the heater. Call
your dealer and arrange for proper servicing.



It is imperative that control compartments, screens, or circulating air passageways of the heater be
kept clean and free of obstructions. These areas provide the air necessary for safe operation.



Do not operate the heater if it is not operating properly in any fashion or if you are uncertain. Call
your dealer for a full explanation of your heater and what to expect.



Do not store or use gasoline or other flammable liquids in the vicinity of this heater.



Do not operate if any portion of the heater was submerged in water or if any corrosion occurs.
Immediately call a qualified service technician to inspect the appliance and to replace any part of thecontrol system and any gas control which has been under water.



Do not place clothing or other flammable items on or near the heater. Because this heater can becontrolled by a thermostat there is a possibility of the heater turning on and igniting any items placedon or near it.

Light the heater using the built-in igniter. Do not use matches or any other external device to lightyour heater.



Never remove, replace, modify or substitute any part of the heater unless instructions are given in thismanual. All other work must be done by a trained technician. Don't modify or replace orifices.



The viewing glass should be opened only for conducting service.



Any safety screen or guard removed for servicing must be replaced prior to operating the heater.

© Travis Industries

4110505

100-01263_000

Safety Precautions

5

Safety Warnings (continued):Allow the heater to cool before carrying out any maintenance or cleaning.



Operate the heater according to the instructions included in this manual.



If the main burners do not start correctly turn the gas off and call your dealer for service.

This unit is not for use with solid fuel.



Do not place anything inside the firebox (except the optional artwork).



Warning: Do not operate appliance with the glass front removed, cracked or broken. Replacementof the glass should be done by a licensed or qualified service person.



Do not throw this manual away. This manual has important operating and maintenance instructions
that you will need at a later time. Always follow the instructions in this manual.

Young children should be carefully supervised when they are in the same room as the appliance.
Toddlers, young children and others may be susceptible to accidental contact burns. A physicalbarrier is recommended if there are at risk individuals in the house. To restrict access to a fireplaceor stove, install an adjustable safety gate to keep toddlers, young children and other at risk individuals
out of the room and away from hot surfaces.

Children and adults should be alerted to the hazards of high surface temperature and should stayaway to avoid burns or clothing ignition. Do not touch the hot surfaces of the heater. Educate all
children of the danger of a high-temperature heater.



Due to the high temperature, the heater should be located out of traffic and away from furniture anddraperies.



Instruct everyone in the house how to shut gas off to the appliance and at the gas main shutoff valve.
The gas main shutoff valve is usually next to the gas meter or propane tank and requires a wrench to
shut off.

Travis Industries, Inc. grants no warranty, implied or stated, for the installation or
maintenance of your heater, and assumes no responsibility of any consequential damage(s).

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

6

6

Installation Options








Residential or Mobile Home
Straight or Corner Placement
Flush or Recessed Face

Raised or Floor Placement
Internal or External Chase
Bedroom Approved

Heating Specifications
Natural Gas

PropaneUp to 1,700

Up to 1,700

35,00035,000Approximate Heating Capacity (in square feet)*
Maximum BTU Input Per Hour***

Heating capacity will vary with floor plan, insulation, and outside temperature.
Efficiency rating is a product thermal efficiency rating determined under continuous operation
independent of installed system.

Dimensionsba31-3/4”807mm

36-1/2”928mm

6-1/4”
159mm

33-1/4"845mm

30-1/4"768mm
18.75"
476mm
28-3/4"730mm.5"32 m m6
2
8

1” 25mm

30"
762mm

R
arrearie're

16-1/2”426mm

36.25"
921mm

e
ft ch
Le gaua'ht
RigoitdrF
av rontant(a) Center Location of Vent(b) Heat Shield (must be bent vertically after fireplace is in location)© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

7

Packing List

Propane Conversion Kit
564 HO Thimble (250-02318)

Additional Items Required Direct Vent


Gas Line Equipment
Electrical Equipment

This Fireplace Requires a Burner Kit, Firebacks, Logs/Media, and Face/Grill
This fireplace is shipped without a burner. This allows the fireplace to be configured in one of threeunique designs. See the table below to verify you have all of the items required.

Burner Style

EmberFyre™ Burner
96900116

Logs/Media

Requires 564 Ceramic
Firebacks:
96100179
96100181
96100182
96100183
96100270
96100271
Included w Burner

Face/Grill

Use any 564 Face or Grill

Firebacks© Travis Industries

DiamondFyre™
Burner96900115
Requires one of thefollowing:
Stainless 96100249
Enamel Black 96100250
Painted Black 96100251

Use 564 HO (31 DVI)Media
Driftwood (94500548)
Other Media To Follow
Use any 564 Face or Grill

4110505

DancingFyre™ Burner
96900114
Included w Burner(Black Painted)
NOTE: You may use
ceramic or 564 HO
DiamondFyre firebacks,
but they are only installedon the firebox walls (floor
firebacks are discarded).
Included w Burner

Use any 564 Face or Grill

100-01263_000

Installation (for qualified installers only)

8

8

Installation OverviewAll requirements below must be met.
See the section“Vent Requirements”

See the section“Mantel Requirements”

See the section“Approved Vent
Configurations”

Drywall
DrywallSide
Wall12” min.
305mm

Nailing brackets
See the section“Minimum Framing
Dimensions”

See “Optional NonCombustible Facing”

See “Optional NonCombustible Hearth”

See the section“Gas Line Installation”

See the section“Electrical Connection”

Recommended Installation Procedure

Frame the opening for the fireplace. Make sure to allow for vent installation.

This fireplace is designed to accommodate 1/2" (13mm) or 5/8" (16mm) drywall (see "Nailing
Brackets" on page 12 for details). Secure the fireplace to the framing.



Install the vent, gas line and electrical hook-up.

Install the drywall.



Install the hearth (if applicable).



Install the facing (if applicable).



Install the mantel (if applicable).



Finalize the installation (see page 36) and install the grill or face.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

9

Massachusetts Requirements
NOTE: The following requirements reference various Massachusetts and national codes not contained in this document.

Requirements for the Commonwealth of Massachusetts
For all side wall horizontally vented gas fueled equipment installed in every dwelling, building or structure used in whole or inpart for residential purposes, including those owned or operated by the Commonwealth and where the side wall exhaust venttermination is less than seven (7) feet above finished grade in the area of the venting, including but not limited to decks andporches, the following requirements shall be satisfied:
Installation of Carbon Monoxide Detectors
At the time of installation of the side wall horizontal vented gas fueled equipment, the installing plumber or gasfitter shallobserve that a hard wired carbon monoxide detector with an alarm and battery back-up is installed on the floor level where thegas equipment is to be installed. In addition, the installing plumber or gasfitter shall observe that a battery operated or hard
wired carbon monoxide detector with an alarm is installed on each additional level of the dwelling, building or structure servedby the side wall horizontal vented gas fueled equipment. It shall be the responsibility of the property owner to secure theservices of qualified licensed professionals for the installation of hard wired carbon monoxide detectors.
In the event that the side wall horizontally vented gas fueled equipment is installed in a crawl space or an attic, the hard wired
carbon monoxide detector with alarm and battery back-up may be installed on the next adjacent floor level.
In the event that the requirements of this subdivision cannot be met at the time of completion of installation, the owner shallhave a period of thirty (30) days to comply with the above requirements; provided, however, that during said thirty (30) day
period, a battery operated carbon monoxide detector with an alarm shall be installed.
Approved Carbon Monoxide Detectors
Each carbon monoxide detector as required in accordance with the above provisions shall comply with NFPA 720 and be
ANSI/UL 2034 listed and IAS certified.
Signage
A metal or plastic identification plate shall be permanently mounted to the exterior of the building at a minimum height of eight(8) feet above grade directly in line with the exhaust vent terminal for the horizontally vented gas fueled heating appliance orequipment. The sign shall read, in print size no less than one-half (1/2) inch in size, “GAS VENT DIRECTLY BELOW. KEEP
CLEAR OF ALL OBSTRUCTIONS”.
Inspection
The state or local gas inspector of the side wall horizontally vented gas fueled equipment shall not approve the installation
unless, upon inspection, the inspector observes carbon monoxide detectors and signage installed in accordance with theprovisions of 248 CMR 5.08(2)(a)1 through 4.
Exemptions
The following equipment is exempt from 248 CMR 5.08(2) (a) 1 through 4:• The equipment listed in Chapter 10 entitled “Equipment Not Required To Be Vented” in the most current edition of NFPA 54
as adopted by the Board; and• Product Approved side wall horizontally vented gas fueled equipment installed in a room or structure separate from thedwelling, building or structure used in whole or in part for residential purposes.

MANUFACTURER REQUIREMENTS
Gas Equipment Venting System Provided
When the manufacturer of Product Approved side wall horizontally vented gas equipment provides a venting system design or
venting system components with the equipment, the instructions provided by the manufacturer for installation of the equipment
and the venting system shall include:• Detailed instructions for the installation of the venting system design or the venting system components; and• A complete parts list for the venting system design or venting system.
Gas Equipment Venting System NOT Provided
When the manufacturer of a Product Approved side wall horizontally vented gas fueled equipment does not provide the partsfor venting the flue gases, but identifies “special venting systems”, the following requirements shall be satisfied by the
manufacturer:• The referenced “special venting system” instructions shall be included with the appliance or equipment installation
instructions; and• The “special venting systems” shall be Product Approved by the Board, and the instructions for that system shall include aparts list and detailed installation instructions.
A copy of all installation instructions for all Product Approved side wall horizontally vented gas fueled equipment, all venting
instructions, all parts lists for venting instructions, and/or all venting design instructions shall remain with the appliance orequipment at the completion of the installation.
See Gas Connection section for additional Commonwealth of Massachusetts requirements.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

10

10

Fireplace Placement Requirements


The fireplace requires a 1/2" (13mm) clearance from the angled sides of the fireplace to the framing
members. No material (insulation, framing, etc.) may be placed into this area.



Fireplace must be installed on a level surface capable of supporting the fireplace and vent

Fireplace must be placed directly on wood or non-combustible surface (not on linoleum or carpet)This heater may be placed in a bedroom. Please be aware of the large amount of heat this applianceproduces when determining a location.

Clearances

When installed, walls in front of the fireplace must be a minimum 12" (305mm) to the side of thefireplace.



Due to the high temperature, the heater should be located out of traffic and away from furniture anddraperies.



Fireplace must be placed so the vents below and above the glass do not become blocked.

Raised Fireplaces

The fireplace (and hearth, if desired) may be placed on a platform designed to support the fireplace(155 lbs., 70Kg) and vent.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

11

Minimum Framing Dimensions

Minimum enclosure height = 56” (1422.4 mm)

Route the electrical line to a position
to the left rear of the fireplace.

36.75”
936mm

The on/off switch/thermostat wire
(if used) should be routed to a locationnear the left front of the fireplace.

36.5”
928mm

16.5”
419mm

WARNING: A cut-out for the gas line
may be required on the framing. See
the dimensions under “Gas Line
Connection” for details.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

12

12

Nailing Brackets

There are 4 nailing brackets
on the front of the fireplace.
Follow the directions below to
prepare the nailing brackets.
Once in place, nail or screw thenailing brackets to the framing.

NOTE: Additional nailingbrackets are provided along
the base of the fireplace. Usethese brackets if not using
the front brackets.

WARNING:
Make sure the fireplace issquare and plumb whenplaced in the framing.
Measured corner-to-corner,
the fireplace should be square(approx. 47-1/8” / 1197mm) for
each dimension. Use shims toensure the fireplace is square.

TOP VIEW

1/2” (13mm) Drywall

Framing

For installations using 1/2” (13mm)
facing, fold the larger tab out
90 degrees. Use a screwdriver ifnecessary.

Fireplace

Nailing Bracket
Drywall

5/8” (16mm) Drywall

TOP VIEW

For installations using 5/8” (625mm)
facing, fold the shorter tab out
90 degrees. Use a screwdriver ifnecessary.

Fireplace

Framing

Nailing Bracket
Drywall© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

13

Corner Installations
A typical 45° installation uses the framing dimensions shown in the illustration below (NOTE: allclearances still apply).
Minimum 1/2" (13mm)
C le arance

14-1/4"362mm

44-1/2" Min.
1130mm© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

14

14

Gas Line Requirements
MASSACHUSETTS INSTALLATIONS - WARNING:
THIS PRODUCT MUST BE INSTALLED BY A LICENSED PLUMBER OR GAS FITTER WHEN INSTALLED WITHIN THE
COMMONWEALTH OF MASSACHUSETTS.
OTHER MASSACHUSETTS CODE REQUIREMENTS:


Flexible connector must not be longer than 36 inches.

Shutoff valve must be a “T” handle gas cock.



Only direct vent sealed combustion products are approved for bedrooms or bathrooms.

Fireplace dampers must be removed or welded in the open position prior to the installation of a fireplace insert or gas log.



A carbon monoxide (CO) detector is required in the same room as the appliance.

The gas line must be installed in accordance with all local codes, if any; if not, follow ANSI 223.1 and
NFPA 54(88), in Canada follow CSA B149.1 and the requirements listed below.
The fireplace and gas control valve must be disconnected from the gas supply piping during any
pressure testing of that system at test pressures in excess of 1/2 psig (3.5 kPA). For pressures under
1/2 psig (kPA), isolate the gas supply piping by closing the manual shutoff valve.
Leak test all gas line joints and the gas control valve prior to and after starting the fireplace.




Fuel


This fireplace is designed either for natural gas or for propane (but not for both). Check the sticker on the top of
the gas control valve to make sure the correct fuel is used.

Gas Line Connection
Installation must be performed by a qualified installer, service agency or the gas supplier (In Massachusetts alicensed plumber/gasfitter).
Standard Input Pressure

Gas Inlet Pressure
Natural Gas
Propane

7" W.C. (1.74 kPA)
13" W.C. (2.73 kPA)

If the pressure is not sufficient, make sure the piping used is large enough, the supply regulator is adequately
adjusted, and the total gas load for the residence does not exceed the amount supplied.
The supply regulator (the regulator that attaches directly to the residence inlet or to the propane tank) should
supply gas at the suggested input pressure listed above. Contact the local gas supplier if the regulator is at an
improper pressure.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)15

Gas Line Location

A 6” (152mm) flex tube and shutoff
valve are included with the fireplace.
The shutoff valve accepts a ½” MPT.
8-3/4”
222mm

The gas valve inlet is located 2-½”
above the base of the fireplace.

Right Side Gas Inlet (preferred)

13-3/4” (349mm)

1-3/4”(44mm)/4”
7-3 mm)7(19

Left Side Gas Inlet

8-3/4"
222mm

13-3/4"349mm

4(12 -3/4”
1mm)© Travis Industries

4110505

1-3/4”(44mm)

100-01263_000

Installation (for qualified installers only)

16

16

Electrical Connection (required)The electrical line to the grounded receptacle inside the fireplace must be installed by a qualified
installer and must meet all local codes.

Make sure the household breaker is shut off prior to working on any electrical lines.

The appliance, when installed, must be electrically grounded in accordance with local codes or, in theabsence of local codes, with the National Electrical Code, ANSI/NFPA 70, or the Canadian ElectricalCode, CSA C22.1.

The electrical line must be a min. 14 gauge, and supply 120 Volts at 60 Hz (2 Amps).

Caution:Label all wires prior to disconnection when servicing controls. Wiring errors can cause
improper and dangerous operation.

a© Travis Industriescb4110505d

100-01263_000

Installation (for qualified installers only)

17

Optional Wall Switch or Thermostat Installation
Do not connect 110-120 VAC to the gas control valve or wiring system of this fireplace. The switch andwiring must be installed by a qualified installer.
This fireplace includes an optional wall switch (with wire) to
OPTIONAL WALL SWITCH
operate the fireplace burner without accessing the internal(included with fireplace)on/off switch. A thermostat may be used instead.
Route the wire from inside the fireplace, through the grommet
on either side of the fireplace near the gas inlet (see at right)
to the switch. The wall switch (or thermostat) may bypass thefireplace on/off switch or be installed in parallel or series
Place "WARNING"
label on switch cover.
configuration (see below).
Caution:Label all wires prior to disconnection whenservicing controls. Wiring errors can cause
improper and dangerous operation.

Note:

When using a GreenSmart™ remote, use thereceiver for on/off operation (do not use a wall
switch or thermostat).
Make sure all wiring is secure and does notcontact hot or moving components.

Warning:

Parallel Connection
Thermostat / External
Switch ON
Thermostat / External
Switch OFF

Series Connection

On / Off Switch
ON
Heater is ON

On / Off Switch
OFF
Heater is ON

Heater is ON

Heater is OFF

To wire the heater in parallel, follow the directions below:aThermostat /External Switch ON
Thermostat /External Switch OFF

On / Off Switch
ON
Heater is ON

On / Off Switch
OFF
Heater is OFF

Heater is OFF

Heater is OFF

To wire the heater in series, follow the directions below:ab

On / Off Switchb

On / Off Switch

Thermostat(or External Switch) Wires

Thermostat(or External Switch) Wirescc© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

18

18

Vent Requirements
The gas appliance and vent system must be vented directly to the outside of the building, and never
be attached to a chimney serving a separate solid fuel or gas-burning appliance. Each direct ventgas appliance must use its own separate vent system.



In addition to the requirements listed here, follow the requirements provided with the vent.



The fireplace must use the Travis Thimble (sku 250-02318) whenever the vent penetrates a wall.
Other penetrations only require a 1" (25mm) clearance and may use a standard firestop (make sure
the required 1" (25mm) clearance is met).

Vent Clearances

The vent must maintain the required clearance to combustible materials to prevent a fire. Do not fill
air spaces with insulation.
Sides
1" (25mm)
Above
4" (102mm)
Below
1" (25mm)

V ertical T ermination
Horizontal

Required Thimble

T ermination

Us e a roof flas hing and s torm collar
whenever pas s ing through the roof

S ee C learances Above
Us e a fires top wheneverpas s ing through a ceiling
Us e a s upport box

S ee C learances Above

S ee C learances Aboveon expos ed ventS ee C learances Above

Altitude Considerations
This heater has been tested at altitudes ranging from sea level to 6,000 feet (1800 M). In this testing we havefound that the heater, with its standard orifice, burns correctly with just an air shutter adjustment.



Failure to adjust the air shutter properly may lead to improper combustion which can create a safety hazard.
Consult your dealer or installer if you suspect an improperly adjusted air shutter.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

19

Approved Vent

May use 6-5/8” if terminated vertically.

Horizontal termination configurations use 8" (203mm) diameter Simpson Dura-Vent Model DirectVent Pro (or GS)*.
* Other vent may be approved with this fireplace. Check with the vent manufacturer for details.



Vertical termination configurations use 8" (203mm) or 6-5/8" (168mm) diameter Simpson Dura-Vent
Direct-Vent Pro (or GS)*.

NOTE: Travis Industries strongly recommends using a 6-5/8” diameter vent when terminating
vertically.


NOTE: When using 6-5/8” (168mm) diameter vent, make sure to accommodate the 4” (102mm)
clearance above the vent. Standard firestops do not include this clearance.



Always use the high-wind cap (58DVA-HC, 58DVA-VCH, or 46DVA-VCH).



Installation instructions for Simpson Dura-Vent may be found at www.duravent.com.



Other vents may be approved.

Vent Installation


Slide the vent sections together and turn 1/4 turn until the sections lock inplace.



Screws are not required to secure the vent. However, three screws may be
used to secure vent sections together if desired.

High temperature sealant is recommended at the appliance starter section
connection (use high-temperature silicone or Mill-Pac®).



If disassembly is required, at time of re-assembly check to see if the ventcreates a tight fit. If it does not, apply high temperature sealant to the jointsof the affected sections.

Horizontal sections require a 1/4" (6mm) rise every 12" (305mm) of travelHorizontal sections require non-combustible support every three feet (e.g.: plumbing tape)© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

20

20

Approved Vent Configurations
Restrictor Position


Intake and exhaust restrictors are built into the appliance to adjust the flow rate of intake air andexhaust gases. Depending upon the vent configuration, you may be required to adjust the restrictor
positions. The charts for acceptable vent configurations detail the correct restrictor positions.

Exhaust Restrictor Adjustment
The exhaust restrictor is shipped in position “1”. If the restrictor is required in a different position, remove thescrews, re-position the restrictor (see “A” below), and replace the screws.
In the example “B” below, the restrictor is set in position #3.

FireboBack Wx Roo

fall of F

ireboxaFirebox RoofThis example is Position # 3
Back W

all of F

ireboxb# 1 (open - stock position)#2#3#4# 5 (closed)© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

21

Intake Restrictor Adjustment
The intake restrictor is shipped with the burner. See the burner installation instructions for details on
installing this component.
Make sure to adjust the intake restrictor to the position indicated on the vent configuration page. To
adjust the restrictor, loosen the two screws securing the restrictor to the firebox and slide it to the correct
position as shown below.

Intake Restrictor located on rear wall of firebox

Position #1 (open)

Dancing/DiamondFyre
Intake Restrictor:

6

EmberFyre
Intake Restrictor:

5

4
3
2

6
5
4
3

1

2

1

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

22

22

Diffuser Plate Adjustment
Certain vent configurations require the diffuser plate to be adjusted (refer to the approved ventconfiguration charts for details). Position # 1 is stock (bent). Position # 2 is flattened.
Change the diffuser to position #2 as follows:
1. The diffuser is located above the exhaust restrictor (remove the restrictor if necessary).
2. Remove the diffuser.
3. Bend the round portion of the diffuser so it is flat (position #2).
4. Secure the flattened diffuser plate with the screws removed earlier.
5. Replace the exhaust restrictor. See “Exhaust Restrictor Adjustment” for the restrictor settings.
FireboBack Wx Roo

fall of F

irebox1

1/4” Nutdriver

DIFFUSER SIDE VIEW
3
Before (Stock - Position #1)

After (Position #2)

2

4© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

23

Vent Configurations with Horizontal Termination (EmberFyre Burner only)

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor anddiffuser positions.



Up to four elbows (45° or 90°) may be used.



Only one horizontal elbow may be used.

21' max (6.4m)
20 feet (6m)

20' max (6m)

15 feet (4.5m)

10 feet (3m)0 feet5 feet (1.5m)

NOTE: With no vertical rise, LP installations have a maximum run of 2 feet (0.6m); NG installations have amaximum run of 4 feet (1.2m).

21' max (6.4m)
20 feet (6m)

Exhaust Restrictor #4
Intake Restrictor #4
Exhaust Restrictor # 5
Diffuser Position #2 (OPEN)
Exhaust Restrictor #3
Intake Restrictor #3
Diffuser Position #2 (OPEN)

15 feet (4.5m)

15 feet (4.5m)
Exhaust Restrictor #2
Intake Restrictor #3
Diffuser Position #2 (OPEN)

10 feet (3m)

10 feet (3m)
Exhaust Restrictor #1
Intake Restrictor #1
Diffuser Position #1 (CLOSED)

5 feet (1.5m)

5 feet (1.5m)

2’ LP/4’ NG Maximum

0 feet
20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feetH2This is considered a horizontal
elbow (it does not matter
whether it turns right or left).
It may be a 90° or 45° elbow.
.

Horizontal length (max. 24’) is calculated
by adding both lengths of horizontal run(Horizontal Length = H1 + H2).

H1

© Travis Industries

This is considered a vertical elbow.

4110505

100-01263_000

Installation (for qualified installers only)

24

24

Vent Configurations with Vertical Termination (EmberFyre Burner only)

Only one horizontal elbow
may be used.

40' max (12m)

40' max (12m)

Exhaust Restrictor #5
Intake Restrictor #6
Diffuser #2 (OPEN)

35 feet (10.5m)
Horizontal length (max. 24’) is calculated
by adding both lengths of horizontal run(Horizontal Length = H1 + H2).
This is considered a horizontal
elbow (it does not matter
whether it turns right or left).
It may be a 90° or 45° elbow.
H2

20' max (6m)

Up to four elbows (45° or90°) may be used.

15 feet (4.5m)



10 feet (3m)

The termination must fallwithin the shaded area
shown in the chart. Use theindicated restrictor anddiffuser positions.

0 feet

5 feet (1.5m)

NOTE: Travis Industries strongly recommends using a 6-5/8” diameter vent when terminating
vertically.

35 feet (10.5m)

30 feet (9m)

30 feet (9m)Exhaust Restrictor #4
Intake Restrictor #5
Diffuser #2 (OPEN)

25 feet (7.5m)

Exhaust Restrictor #3
Intake Restrictor #3
Diffuser #2 (OPEN)

25 feet (7.5m).
H1

20 feet (6m)

20 feet (6m)
Exhaust Restrictor #2
Intake Restrictor #2
Diffuser #2 (OPEN)

This is considered a vertical elbow.

15 feet (4.5m)

15 feet (4.5m)
Exhaust Restrictor #1
Intake Restrictor #2
Diffuser #2 (OPEN)

10 feet (3m)

10 feet (3m)

Exhaust Restrictor #1
Intake Restrictor #1
Diffuser #1

5 feet (1.5m)

5 feet (1.5m)

0 feet© Travis Industries

4110505

20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feet100-01263_000

Installation (for qualified installers only)

25

Vent Configurations with Horizontal Termination (Dancing/DiamondFyre)

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor anddiffuser positions.



Up to four elbows (45° or 90°) may be used.



Only one horizontal elbow may be used.

21' max (6.4m)
20 feet (6m)

20' max (6m)

15 feet (4.5m)

10 feet (3m)0 feet5 feet (1.5m)

NOTE: With no vertical rise, LP installations have a maximum run of 2 feet (0.6m); NG installations have amaximum run of 4 feet (1.2m).

21' max (6.4m)
20 feet (6m)

Exhaust Restrictor #4
Intake Restrictor #5
Exhaust Restrictor # 5
Diffuser Position #2 (OPEN)
Exhaust Restrictor #4
Intake Restrictor #3
Diffuser Position #2 (OPEN)

15 feet (4.5m)

15 feet (4.5m)
Exhaust Restrictor #3
Intake Restrictor #2
Diffuser Position #2 (OPEN)

10 feet (3m)

10 feet (3m)
Exhaust Restrictor #1
Intake Restrictor #1
Diffuser Position #1 (CLOSED)

5 feet (1.5m)

5 feet (1.5m)

2’ LP/4’ NG Maximum

0 feet

20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feetH2This is considered a horizontal
elbow (it does not matter
whether it turns right or left).
It may be a 90° or 45° elbow.
.

Horizontal length (max. 24’) is calculated
by adding both lengths of horizontal run(Horizontal Length = H1 + H2).

H1

© Travis Industries

This is considered a vertical elbow.

4110505

100-01263_000

Installation (for qualified installers only)

26

26



The termination must fallwithin the shaded area
shown in the chart. Use theindicated restrictor anddiffuser positions.



Up to four elbows (45° or90°) may be used.



Only one horizontal elbow
may be used.

20' max (6m)

15 feet (4.5m)

10 feet (3m)0 feet

NOTE: Travis Industries
strongly recommends using a
6-5/8” diameter vent whenterminating vertically.

5 feet (1.5m)

Vent Configurations with Vertical Termination (Dancing/DiamondFyre)

40' max (12m)

40' max (12m)

35 feet (10.5m)

35 feet (10.5m)

Exhaust Restrictor #5
Intake Restrictor #6
Diffuser #2 (OPEN)

30 feet (9m)

30 feet (9m)Horizontal length (max. 24’) is calculated
by adding both lengths of horizontal run(Horizontal Length = H1 + H2).
This is considered a horizontal
elbow (it does not matter
whether it turns right or left).
It may be a 90° or 45° elbow.
H2

Exhaust Restrictor #5
Intake Restrictor #5
Diffuser #2 (OPEN)

25 feet (7.5m)

20 feet (6m)

25 feet (7.5m)

20 feet (6m)

Exhaust Restrictor #4
Intake Restrictor #3
Diffuser #2 (OPEN).
H1

This is considered a vertical elbow.

15 feet (4.5m)

15 feet (4.5m)
Exhaust Restrictor #2
Intake Restrictor #3
Diffuser #2 (OPEN)

10 feet (3m)

10 feet (3m)
Exhaust Restrictor #1
Intake Restrictor #1
Diffuser #1

5 feet (1.5m)

5 feet (1.5m)

0 feet© Travis Industries

4110505

20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feet100-01263_000

Installation (for qualified installers only)27

Termination Requirements! Venting terminals shall not be recessed into a wall or siding.
A
B
C

D

E

F

G
H
I
J
K
L
M
N

Minimum 9" (229mm) clearance from any door or window
Minimum 12" (305mm) above any grade, veranda, porch, deck or balcony
Minimum 1" (25mm) from outside corner walls
NOTE: Clearance in accordance with local installation codes and the requirementsof the gas supplier.
Minimum 1" (25mm) from inside corner walls
NOTE: Clearance in accordance with local installation codes and the requirementsof the gas supplier.

Roof
SurfaceRoof
Eaves

11" Min.
(279mm)6" Min.
(152mm)Minimum 11" (279mm) clearance below unventilated soffits or roof surfaces.
Minimum 18" (457mm) clearance below ventilated soffits.
Minimum 6" (152mm) clearance below roof eaves.
NOTE: Vinyl surfaces require 24" (610mm)
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.
Minimum 12" (305mm) clearance below a veranda, porch, deck or balcony.
NOTE: Permitted only if veranda, porch, deck, or balcony is fully open on a minimum of two sides beneath the floor.
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.
Minimum 48" (1219mm) clearance from any adjacent building.
Minimum 84" (2134mm) clearance above any grade when adjacent to public walkways or driveways.
NOTE: may not be used over a walkway or driveway shared by an adjacent building.
Minimum 9" (229mm) clearance to any non-mechanical air supply inlet to the building or the combustion air inlet
to any other appliance.
Minimum 36" (914mm) clearance above any mechanical air supply inlet if within 10’ (3M) horizontally.
Minimum 36" (914mm) from the area above the meter/regulator (vent outlet) - this extends 15’ (4.5M) above the regulator
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.
Minimum 36" (914mm) from the meter/regulator (vent outlet).
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.
Minimum 12” (305mm) above the roof line (for vertical terminations).
Minimum 24” (610mm) horizontal clearance to any surface (such as an exterior wall) – for vertical terminations.
E
N
M

E
E

A

K
G

J

A
F

H

D

I

C
L
B

NOTE: Measure clearances to the nearest edge of the exhaust hood.

••

Use the vinyl siding standoff when installing on an exterior with vinyl siding.
Vent termination must not be located where it will become plugged by snow or other material© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

28

28

Hearth Requirements
Do not build a hearth morethan 1" (25mm) above thebaseplate (this area mustremain clear for the accessdoor).

Floor Mounted
Fireplaces

If installed near carpet or othercombustible flooring, the fireplacemust be raised so the base of theunit is above the carpet surface or
flooring material.

WARNING:
A non-combustible hearth is not required. However, if theheater is installed next to the floor, we recommend ahearth to protect the flooring surface from discoloration orother negative impact from the heater.

RaisedFireplaces

A hearth is not required when thefireplace is raised above the flooring surface.

Fireplace Stand© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

29

Facing Requirements


The included fiber board is required and must remain attached to the fireplace (see “a” below).



Non-combustible facing must extend 3” (77mm) above the face of the fireplace (see “c” below).
Drywall or other combustible may not be place on top of this non-combustible area.

Drywall (or other combustible) may be placed above the non-combustible facing (see “b” below) andto the sides and below the fireplace face. This combustible facing must be a minimum 3” (77mm)
above the face of the fireplace (see “b” below).



Tile or other non-combustible facing may be placed along the perimeter of the fireplace face, but must
not extend over the glass/grill opening (see “d”). This area must remain open to allow for glass frame
removal and air flow.

Drywall Installation
a

b
b

c

} 3” (77mm)

c

d

a

b

b

(a) Fiber Board (included with fireplace)(c) Tile (or other non-combustible)(b) Drywall (or other combustible)(d) Perimeter of Fireplace (may be covered)© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

30

30

Facing Overview
Upgrade faces are available for this fireplace and may influence facing installation. Consult with yourTravis Dealer if you are using an upgraded face.

Masonry Line
Tile Line

Tile Line
Masonry Line

An optional non-combustible facing may be installed on the fireplace. Use the guidelines below todetermine the location (also see the following pages for detailed diagrams.
Tile LineAny non-combustible facing under 1" (25mm) thick (see "Thin Facing" on page 31).
Masonry Line Any non-combustible facing over 1" (25mm) thick (see "Thick Facing" on page 33).
Hearth Line
Non-combustible hearth/facing should be installed up to this location (1" (25mm) above the baseof the fireplace). The fireplace may be raised to accommodate thicker hearth materials.

e

nry

Lin

so
Ma
e
n
i
eL

Til

all

yw
Dr

all

yw

Dr

e
Lin neLinry
so Tile
a
M

e

rth

Lin

Tile Line
Masonry Line

a
He

e

rth

Lin

a
He

Masonry Line
Tile LineNOTE: The hearth or facing can extend nogreater than 1" above the base of the fireplace.
The fireplace may be raised to accommodate
thicker hearth materials.

Optional Faceplates – Sizing ChartName
FPX Artisan, Classic, Fr Ctry
Wilmington
Victorian Lace
Bungalow, Tree of Life

© Travis Industries

Height29”(737mm)
29”(737mm)27-1/2”(699mm)27-1/2”(699mm)Width
36”(914mm)
36”(914mm)32-3/8”(822mm)32-3/8”(822mm)Notes
61” Radius – May fit over top of tile facing
May fit over top of tile facing
Optional facing will abut the edge of faceplate (tileline)
Optional facing will abut the edge of faceplate (tileline)

4110505

100-01263_000

Installation (for qualified installers only)

31

Thin Facing Installation (tile, marble, or other non-combustible under 1" (25mm) thick)

Tile Line

Upgrade faces are available for this fireplace and may influence facing installation. Consult with yourTravis dealer if you are using an upgraded face.

Tile

Lin

e

Attach the facing to this edge of the fireplace.

Do not install tile or other material in frontof the glass frame, convection channel,
or access panel openings. This area mustremain open to access internal components and for convection air.

rth

Lin

e

Tile LineaHe

Floor-mounted fireplaces or raised hearths:
Build the hearth above the fireplace to a
maximum of 1” (25mm). The fireplace may
be raised to accommodate thicker hearth materials.

TOP VIEW
Framing

Fireplace

Nailing Bracket

Raised fireplaces:
Install the facing above the fireplace
to a maximum of 1” (25mm).

Drywall

FRONT VIEW
1-1/2"
38mm
Tile

27-3/4"705mm

NOTE FOR FPX FACES:FPX arched faces require the FPX Face Upgrade Kit(sku 98500683) and a triangular piece of facing inthese upper corners. See the instructions included withthe face for details.
7-1/2"
191mm© Travis Industries

1”

1-5/8"

32-1/2"

1-7/8"

41mm

826mm

48mm

4110505

100-01263_000

Installation (for qualified installers only)

32

32

Thin Facing Installation (tile, marble, under 1" (25mm) thick) — Side View

Raised Fireplace
Tile or other facing under 1’’ (25mm)(with no Hearth)

thick.

Face

SIDE OFFIREPLACE

Note how the facing extends 1’’ (25mm)
above the base of the fireplace.

1’’ (25mm)
Fireplace Support
Floor

Floor-Mounted Fireplace(with Hearth)

Tile or other facing under 1’’(25mm) thick.

Face

SIDE OFFIREPLACEHearth: note how it extends under the face max. 1’’ (25mm) thick. The fireplace may beraised to accommodate thicker hearthmaterials.

Max. 1’’ (25mm)
Floor© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

33

Thick Facing Installation (stone, brick, or other non-combustible over 1" (25mm) thick)Masonry LineIf using a Fireplace Xtrordinair (FPX) arched face, see "Thick Facing with a Fireplace Xtrordinair Arched
Faces" on page 34.

Do not install masonry or othermaterial in front of the fireplace. This area
must remain open to install the face.

so
Ma

hL

Lin

e

ine

Masonry Line

H

rt
ea

nry

Floor-Mounted Fireplaces or Raised Hearths:
Build the hearth 1” maximum (25mm) above thebase of the fireplace. The fireplaces may be raisedto accommodate thicker hearth materials.

TOP VIEW - Protruding Masonry
Framing

Fireplace

Nailing Bracket
Drywall

Raised Fireplaces:
Masonry is installed 1” (25mm)(maximum) above the baseof the fireplace.

FRONT VIEW

Masonry

TOP VIEW - Recessed Masonry
Framing
29-1/4”743mm

Fireplace
Drywall

Masonry1”
25mm

NOTE: The nailing brackets are not used for this typeof installation -- secure the fireplace to the floor withthe brackets along the base of the fireplace.

© Travis Industries

36-1/4”921mm

4110505

100-01263_000

Installation (for qualified installers only)

34

34

Thick Facing with Fireplace Xtrordinair (FPX) Arched Faces
The following illustration shows facing considerations for those fireplaces utilizing FPX arched faces.
The facing must be non-combustible and over 1" (25mm) in depth.

Masonry LineThe Fireplace Xtrodinair 564
Masonry Template is recommended
for masonry installation (sku98500674). The template helps
locate and support the masonry as it
is installed.

He

arth

Lin

e

Floor-Mounted Fireplaces or Raised Hearths:
Build the hearth above the fireplace to a maximumof 1” (25mm). The fireplace may be raised toaccommodate thicker hearth materials.
Before installing the masonry,
install the FPX FaceUpgrade Kit(98500683). This kit covers theupper corners.

Raised Fireplaces:
Install the masonry above the baseof the fireplace to a maximum of 1” (25mm).

FRONT VIEW

2-3/4”
70mm

TOP VIEW
Framing
Fireplace

Nailing Bracket

61” Radius (1549mm)

29”
737mm

Drywall

Face

Masonry1"
25mm
36-1/4”921mm© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

35

Thick Facing Installation — Side View

Floor-Mounted Fireplace(with Hearth)
Masonry or other non-combustible
over 1’’ (25mm) thick

SIDE OFFIREPLACE

Face
Hearth (note how it extends under the face - max. 1’’(25mm) thick). The fireplace may be raised toaccommodate thicker hearth materials.

Max. 1’’ (25mm)
Floor

Raised Fireplace(with no Hearth)
Masonry or other non-combustible
over 1’’ (25mm) thick.

SIDE OFFIREPLACE

Face (Behind Masonry)
The masonry extends 1’’ (25mm)
above the base of the fireplace.

1’’ (25mm)
Fireplace Support
Floor© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

36

36

Mantel Requirements
Combustible Mantels


Use the table below to determine the maximum mantel depth allowed. The mantel depth (measured
from the face of the fireplace) must fall in the shaded portion of the table.



Any material that protrudes more than 3/4” (19mm) from the non-combustible facing is considered amantel and must meet the mantel requirements.

Mantel Columns
0"(0
1 " mm)(2
2 " 5mm(51 )m
3"(7 m )
4 " 6mm(1)
5" 02m(12 m)
7mm
6"(1)
7" 52mm
(17
8m )
8"
m)
(2
9" 03mm(2)
10 29mm)"(
11 254m" (2m
12 79m )
" (3
m
05 )
mm
)

Maximum Mantel Depth (b)49" (1245mm)
48”

MantelHeightAbove
Base (a)

47”
46”
45”
44”
43”
42”

41" (1042mm)
40”
39”
38”
37”
36”
35”

34" (864mm)

EXAMPLE:You may have a 4” mantel at 43”.

Combustible mantel columns (legs) that protrude more than 3/4” (19mm)
from the glass frame must meet the 12” (229mm) sidewall clearance. If they
protrude 3/4” (19mm) or less, they must meet the facing clearance, 2-1/4” (57mm)
from the glass frame -- to the side of the fireplace, not in front of it.
Non-combustible mantel columns do not have a minimum clearance.

EXAMPLES: You may have a 4” mantel at a minimum 43” above the base of the fireplace.
 At 46”, the maximum mantel depth is 8”.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

37

Steps for Finalizing the Installation
1.
2.
3.

4.

Remove the glass (see page 39).
NOTE: If using propane (LP) convert the appliance prior to installing the logs.
We recommend you purge the gas line at this time (with the glass removed). This allows gas to be detectedonce it enters the firebox, ensuring gas does not build up.
Make sure the two accent light bulbs are in place.
NOTE: Take care to not touch the bulb with your fingers (use a cloth or paper towel).
Install the four AA batteries (included in the owner’s pack) into battery holder (see the illustration below). The AA
batteries act as a power backup in case the household (AC) power goes out. Install the 9v battery (included in
the owner’s pack) into control panel light assembly (see the illustration below). The battery holder is held inplace with Velcro and may be removed for easier access.

Battery Holder for
Control Panel Lights
9
Ba v
tte
ry

AA
AA

Ba

tte

Ba

tte

Lift up and swing the lower
grill down to acces the area

Swing the concealment
cover up and slide it back to

below the firebox.

expose the controls.

ry

ry

AA
Battery
AA

AA
Ba
tte
Ba
ry
tte
ry

HolderAA Battery Tray

5.
6.
7.
8.

Install the Burner/Logs Kit (see the Burner instructions).
Replace the glass.
Start the heater.
Leak test all gas joints.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

38
9.

38

Check the air shutter following the directions below.

Air Shutter Adjustment
Let the heater burn for fifteen minutes (make sure the logs and glass are in place). The flames should beyellow with no sooting. Adjust the air shutter, if necessary, to achieve the correct looking flame.

Correct

Not Enough Air

Too Much Air

Flames should be blue at thebase, yellow-orange on the top.

If the flames are too tall or sooty on theends, open the air shutter.

If the flames are all blue andshort, close the air shutter.

Air Shutter Adjustment

Front Burner Air Shutter Control(RED)
Left = More Air
Right = Less Air

Rear Burner Air Shutter Control(GOLD)Left = Less Air
Right = More Air

NOTE: You may wish to use pliers to adjust
the front air shutter. Typically, the front air
shutter is fully closed (left) on NG, and fully
open (right) on LP.

10. Turn the flame adjust knob to its highest position - the flames should not contact the top of the firebox. Check the flameon low position. The flames should burn off of each burner hole. If the heater does not work correctly, contact your Travis
dealer for a remedy.
11. Give this manual to the home owner for future reference and fully explain operation of this heater. For comprehensive
operating and maintenance instructions, refer to the Owner's Manual.
ACID WASH WARNING: Before installing the faceplate, make sure any masonry that has been treated with acid wash has
been properly neutralized (this is used primarily with brick faces). Acid wash (muriatic acid) is used to remove excess mortar.
If not properly neutralized with an ammonia solution, the plated face may develop a permanent tarnish when the acidevaporates over time. Contact your dealer if uncertain your facing has been properly neutralized.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

39

Glass Frame Removal and Installation
Warning:
Warning:a

The appliance must be completely cool before removing the glass.
Do not strike or slam the glass.

Depending on the face being used, either:
1) Swing the access door down and remove the top grill, or2) Remove the face by unscrewing it or lifting it off -- see
the instructions included with the face for details.
Open the 4 latches holding the glass frame in place,starting with the bottom. Follow the instructions shown to the right.

Top ofFirebox

Latch

Glass

Lift the glass frame up andb pull it forward to remove.

NOTE:
You may need to lift
the glass frame
while re-attaching.

Catch onglass frame

Re-Attaching the Glass Frame:
1) Hang the glass frame on the firebox.
2) While holding the frame in place, attach the upper latches(follow the instructions to the right in reverse).
3) Lift the glass frame slightly and attach the lower latches.
NOTE: Make sure the glass frame is fully in place -- it should
be flush with the front of the fireplace when installed correctly.

© Travis Industries

4110505

100-01263_000

Installation (for qualified installers only)

40

40

Glass Frame Removal and Installation (continued)
The latch can come loose from glass frame anchor. This occurs when it is turned 1/4 turn when it isdisengaged. Follow the directions below to re-install the latch if it becomes loose.

Hold the latch at an angle and insert it into the slot on the glass frame anchor.

Latch

NOTE: this slot may be at adifferent angle than illustrated.
Top ofFireboxGlass Frame
Anchor

Note how the washer on the latch fits behind the flange on theglass frame anchor.

Once fully inserted, turn the latch until it is upright.

© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

41

LP Conversion Instructions
WARNING
This conversion kit shall be installed by a qualified service agency in accordance with the manufacturer’s
instructions and all applicable codes and requirements of the authority having jurisdiction. If theinformation in these instructions is not followed exactly, a fire, explosion or production of carbon
monoxide may result causing property damage, personal injury or loss of life. The qualified service
agency is responsible for the proper installation of this kit. The installation is not proper and complete until
the operation of the converted appliance is checked as specified in the manufacturer’s instructions
supplied with the kit.
Install the LP conversion kit prior to installing the burner.
Remove the glass (see page 36).

Installation
1. Remove the burner bracket as shown below.

© Travis Industries

4110505

100-01263_000

42

Optional Equipment (for qualified installers only)42

2. Replace the orifices as shown below.

Rear Burner Orifice

Front Burner OrificeabcThread Sealant

1/2" Wrench

15/16"
24mm
Orifice ID

Orifice
NG
LP

Front
#50
1.1mm

Rear
#44
#55

3. Install the LP burner bracket and manifold seal plate as shown below. These components areshipped with the fireplace.

© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

43

4. Remove the pilot orifice following the instructions below. Replace with the propane pilot orifice.
a Lift the pilot hoodc Remove the orifice and replace with the LP orifice. Screw theorifice all the way in and replace the pilot hood.

off the pilot
assembly.

Orifice Identification:
LP (Propane) Orificeb

35

Use a hex wrench to35

unscrew the orifice.

NG (Natural Gas) Orifice62
5/32" Hex

NOTE: when re-attaching,
this pin lines up with thenotch in the pilot hood.

Figure 1: Pilot Orifice Removal

5. Remove and discard the screws (see “a” below) holding the stock regulator in place (see “b” below).
Remove the stock regulator and gasket (see “c” below). Place the LP regulator in place, making surethe pre-fitted gasket (see “c” below) is in place.
NOTE: There is a label on the base of the regulator knob indicating regulator type (NG or LP).
Secure the regulator with the screws included with the regulator – tighten to 25 lb.-in of torque (2.82
NM). Place the included label on the valve body where it can be easily seen to insure proper
identification.
NOTE: Leak test this area after the heater is installed, gas is connected, and the main burner is lit.

aT-20 Torx or
Slotted ScrewdriverbcdFigure 2: LP Regulator Placement

6. Install the burner (see the instructions included with the burner). Replace the glass and restore
the fireplace to the correct configuration.

© Travis Industries

4110505

100-01263_000

44

Optional Equipment (for qualified installers only)

44

Attaching the Power Heat Duct to the 564 HO
One or two optional power heat ducts (sku 98500769) may be attached to the 564 HO. The ducting is
attached to the top of the fireplace (left or right side). See the directions below for removing the powerheat duct covers.

Power Heat Duct Covers
1. Remove the outer heat duct plate (4 screws - see picture below).

2. Remove the inner heat duct plate (2 screws – see picture below).

© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)
3

45

Remove the screw on the lower duct plate and rotate it away to allow air to flow from the lower
convection channel (see pictures below). NOTE: This plate is not removed, it is swiveled out of theway – use a screwdriver, if necessary to rotate the plate.

Installing the Power Heat Duct with the 564 HO
The power heat duct must be installed in accordance with the instructions included with the kit and all
local codes. See the illustration below for an overview
Floor
Boot

Electrical Source
Junction Box

Maximum Duct
Length = 20'

Rheostat(with cover plate)
BlowerBox

Use 10” x 3-1/4”
wall stack (duct)when passing
through tightareas.

Duct Adapter(6” Round to 10” x 3-1/4”)
6" Duct
Starter Ring

Power Supply

RheostatJunction Box

Grill© Travis Industries

Hot(black)Hot(black)Common(white)Common(white)Ground(green)Ground(green)BlowerAssembly

Wall Adapter(for use on
2 x 4 walls)

4110505

100-01263_000

Optional Equipment (for qualified installers only)

46

46

GreenSmart™ Remote Control Installation
Packing List















Transmitter
Receiver (with Cover Plate & Switch)
Fan Control Module
VelcroLP or NG Stepper Motor (with screws and label - attaches to Valve)
Wire Harness(2) Power Leads(4) AA Batteries (inside receiver box)
(2) #8 x ½” Machine Screws(2) Wire Ties
Torx T-20 Wrench
Wall Mount (for placing the transmitter on a wall)(2) Drywall anchors (for wall mount)(2) #8 x 3/8” Type B Screws© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

47

Overview
The GreenSmart remote installs onto a 564 fireplace and replaces the stock wiring harness. Before
installing, familiarize yourself with the stock and updated wiring diagrams (see the illustrations on thispage and and following page).
Stock Wiring Diagram
Spark RodAccentLight (s)Pilot
SensorAccent Light
Rheostat
Pilot Ground
Optional
BlowerHookup

CN4

Comfort Control
Valve

PILOT
SENSOR

120 VACPower In

DIGITALFIREPLACE

CN0

BURNERAC
ADAPTERCONTROLSPARK RODVALVEDIAGNOSTICCOMMAND

POWER

CN1

GROUND

CN2

POWER SUPPLYBlack

IPI / CPI

Red
Black
Red

Blue

Red

Red

ON / OFF

Blue

Green

Red

OrangeYellow / Green

VALVE

CN3

Green
White

Black

Blue

White

CONTINUOUS
PILOT

COMFORT
CONTROLGREENSMART
PILOT© Travis Industries

4110505

AA
BATTERY
TRAY

MAIN BURNER

100-01263_000

48

Optional Equipment (for qualified installers only)

48

GreenSmart Wiring Diagram
CN4

Comfort Control
Valve

Spark Rod

Pilot
SensorPILOTSENSOR

DIGITALFIREPLACE

CN0

BURNERSPARK ROD

Pilot
GroundCONTROLVALVEDIAGNOSTICCOMMANDGROUND

POWER

CN1

CN2

STEPPER MOTOR

CN3

BURNER CONTROLVALVERECEIVER
OrangeGreen
Yellow / Green

RemoteReceiver
IPI / CPI

Blue

TOP

White

CONTINUOUS
PILOT(4) AA Batteries

FAN CONTROLFan Controller
POWER

INTERMITTENT
PILOT

110V OUTFAN

AUX OUT

120 VACPower InCOM

AccentLight (s)Thermodisk
Optional
Blower(s)Accent Light
Rheostat© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

49

Installation
WARNING:

Make sure power to the fireplace has been shut off prior to installation.

NOTE:

Refer to the wiring diagram on page 62 while making wiring harness connections.

1

Remove the concealment cove (see Figure 3).

Figure 3

2

Unscrew the four screws holding the control cover in place (see Figure 4). Carefully remove thecontrol cover (see Figure 5)

Figure 4

3

Figure 5

Unplug the ac adapter from the power harness (see Figure 6). You can leave the ac adapter
plugged into the wiring harness.

Figure 6© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

50
4

50

Disconnect the molex connector leading to the gas control valve (see Figure 7).
WARNING: The tabs on the gas control valve are fragile. Take care when removing the molex
connector to not pull or damage the wires or tabs.

Figure 75Disconnect the two leads on the back of the control panel for the IPI / CPI switch (continuous pilot/ greensmart pilot – see Figure 8).

Figure 86Disconnect the comfort control valve connection (see Figure 9). Disconnect the burner control
connector from the fireplace burner control (see Figure 10).

Figure 9© Travis Industries

Figure 104110505

100-01263_000

Optional Equipment (for qualified installers only)
7

Unscrew the on/off/battery plate from the control panel (see Figure 11). Pull the plate and wiringforward (see Figure 12).

Figure 12

Figure 118

The control panel has plastic wire-locks attached to the back (see Figure 13). Un-hook the wires
from the wire-locks and remove the wiring harness, plate, battery holder, and ac adapter (seeFigure 14). These items may be discarded.

Figure 13

951

Figure 14

Use the included torx wrench to remove the stock regulator (see Figure 15). These items may bediscarded.

Figure 15© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

52
10

The stepper motor (adjustable regulator) has an installation sheet included with it – make sure tofollow all of the directions. Place the stepper motor on the gas control valve (see Figure 16) –MAKE SURE IT IS CORRECTLY ORIENTED. Secure using the screws included with the motor(see Figure 17) – tighten to 25 Lb-inches. Leak test this area after installation to verify proper
installation.

Figure 17

Figure 16

11

52

Place the GreenSmart wiring harness in front of the fireplace, noting the position of eachconnector (see .Figure 18).

Figure 18

12

Attach the wiring harness to the burner control (see Figure 19). Attach the gas control valve
molex connector (see Figure 20).

Figure 19© Travis Industries

Figure 204110505

100-01263_000

Optional Equipment (for qualified installers only)
13

Attach the blue and white wires to the IPI/CPI switch (see Figure 21). Connect the wiring harness
to the stepper motor (see Figure 22).

Figure 22

Figure 21

14

53

Attach the wiring harness to the comfort control valve connection (see Figure 23).

Figure 23

15

Place the fan controller near the front of the fireplace to the left and connect it to the wiring
harness (see Figure 24). Attach the power cord from the fan controller to the AC connection (seeFigure 25). MAKE SURE TO TURN THE FAN CONTROLLER ON (“-“ SYMBOL).

Figure 25
Figure 24© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)

54
16

54

Disconnect the power lead from accent light and connect it to the power lead included with this kit(see Figure 26). Attach the power lead to the fan controller in the “AUX OUT” receptacle (seeFigure 27).

Figure 26

Figure 27

NOTE: If using the optional fan, you will want to disconnect its power lead and connect it to
the extra power lead included with this kit, then connect it to the “FAN” receptacle on
the fan controller.
17

Attach the included velcro to the bottom of the fan control module and to the base of the fireplacenear back left of the fireplace. Slide the fan controller into place and secure using the velcro (seeFigure 28).

Figure 28© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)
18

Pull the “RECEIVER” connector through the control panel and attach to the receiver (see Figure29). Then attach the receiver to the control panel with the two #8 machine screws (see Figure
30).

Figure 30

Figure 29

19

Place batteries into the receiver and transmitter (see Figure 31). Calibrate the receiver to thetransmitter (see Figure 32 - use a paperclip to press the “PRG” button, let it beep, then press any
button on the transmitter – the receiver should beep 5 times – see the operating instructions forfurther details).

Figure 32

Figure 31

20

55

Place the receiver coverplate (and switch) over the receiver (see Figure 33) and attach with thetwo screws included with the receiver (see Figure 34)

Figure 33© Travis Industries

Figure 344110505

100-01263_000

Optional Equipment (for qualified installers only)

56
21

Clip any excess wiring into the wire clips on the back of the control panel (see Figure 35). Use
the included wire ties, if necessary, to keep all wiring from contacting any hot or moving
components. Re-attach the control panel (see Figure 36) and shroud (see Figure 3).

Figure 36

Figure 35

2256

A wall mount is included with this kit for the remote. It may be mounted to the wall for easy
access and storage. Use the included drywall anchors (and screws) to secure it to the wall (seeFigure 37).

Figure 37

23

Restore power to the fireplace and test operation of the remote (see the instructions included withthe remote).

© Travis Industries

4110505

100-01263_000

Optional Equipment (for qualified installers only)© Travis Industries

411050557

100-01263_000

58

Index

Index
Additional Items Required .................................... 7
Air Shutter Adjustment ......................................... 38
Altitude Considerations ........................................ 18
Approved Vent Configurations ............................. 20
Approved Vent ..................................................... 19
Clearances ........................................................... 10
Corner Installations ............................................. 13
Diffuser Plate Adjustment..................................... 22
Dimensions .......................................................... 6
Electrical Connection (required) ........................... 16
Exhaust Restrictor Adjustment ............................. 20
Facing Overview .................................................. 30
Facing Requirements ........................................... 29
Features ............................................................... 6
Fireplace Placement Requirements ..................... 10
Fuel ...................................................................... 14
Gas Inlet Pressure ............................................... 14
Gas Line Connection............................................ 14
Gas Line Location ................................................ 14
Gas Line Requirements ....................................... 14
Glass Frame Removal and Installation ................ 39
Hearth Requirements ........................................... 28
Heating Specifications.......................................... 6
Index..................................................................... 58
Installation Options............................................... 6
Intake Restrictor Adjustment ................................ 21
Listing Details ....................................................... 2
Mantel Requirements ........................................... 36© Travis Industries

Minimum Framing Dimensions ............................................11
Nailing Brackets ................................................... 12
Overview .............................................................. 2
Packing List.......................................................... 7
Raised Fireplaces ................................................ 10
Recommended Installation Procedure ................ 8
Restrictor Position ................................................ 20
Safety Precautions ............................................... 4
Thick Facing Installation with FPX Arched Faces 34
Thick Facing Installation ...................................... 33
Thin Facing Installation ........................................ 31
Vent Configurations with Horizontal Termination 23
Vent Configurations with Vertical Termination ..... 24
Vent Clearances .................................................. 18
Vent Installation ................................................... 19
Vent Requirements .............................................. 18
Optional Wall Switch or Thermostat Installation .. 174110505

100-01263_000