MWCP SERIESDECK UNIT
R407C

R407H

※optional

R407C/R407H Series [Scroll Type]
MWCP100C

Model
Power supply

MWCP135C
New Light Blue(7.5 BG7/2)And Black

Color of external packaging
★1
★2
★3

★4

Dimensions

HxWxD

mm

1650 x 2000 x 1640

1650 x 2300 x 1640

1650 x 2300 x 1640

Cooling capacity(50/60Hz)kW

88/100120/135

142/157

Cooling water flow

(50/60Hz)

L/min

332/360

461/485551/590

kW

132

170

200/212

Heating capacity
Humidification capacity
Water pressure drop

(50/60Hz)

kg/h

36

4860

kPa

15.9/19.1

24.2/26.4

41.5/46.4

ZR144KTE-TFD-522 x2
ZR72KCE-TFD-522 x1

ZR144KTE-TFD-522 x3
ZR72KCE-TFD-522 x1

ZR144KTE-TFD-522 x4

Model

Scroll type

TypeCompressor

Speed
Power
Current(50/60Hz)(50/60Hz)

r/min
kW

(50/60Hz)A

8.95 × 2 + 4.48 × 1

2900/3450
8.95 × 3 + 4.48 × 1

17.6 x 2 + 9.1 x 1/
18.1 x 2 + 8.8 x 1

17.6 x 3 + 9.1 x 1/
18.1 x 3 + 8.8 x 1

Model

EF-14-193-00

EE-12-087-00

Heat exchanging
tube

Copper pipe TP2(GB/T 1527)

Pipe20(GB 8163)

Plate

Q235B (GB 3274)
111ModelType

4ROWx14FPIx38THx1700mm

4ROWx16FPIx48THx1700mm
Fin heat exchanger

4ROWx16FPIx48THx1700mm

Material

Heat exchanging
tube

Copper pipe

Fin

Anticorrosion aluminum
SYQ400K,SHAFT+180-R90°

Model
Type

SYQ450K,SHAFT+180-R90°
Centrifugal

SYQ450K,SHAFT+180-R90°

Air flow(50/60Hz)m /min175/175

220/220283/283

External static pressure(50/60Hz)Pa

900/1580

1100/1900

850/1750

kW

7.5

1115

Motor power

Belt transmission

Drive
Steam coilEE-12-086-00

Qty.

Evaporator

Fan

17.6 x 4/18.1 x 4

Shell and tube type

TypeMaterial

8.95 × 4

Direct start

Start method

Condenser

MWCP165C

380V3~/50Hz, 440V/3~/60Hz(220V~/50Hz, 220V~/60Hz)

Main circuit (control circuit)

ModelFin heat exchanger

Material

Cooper pipe and hydrophilic aluminum
Steam spray type

Steam humidifier

Nylon

Filter

Thermal expansion valve
Control panel

Throttling Method
Temperature regulator

100-71-43-14-0
Cooling capacity adjustment range%

100-78-61-39-22-0

100-71-43-29-0
100-71-57-29-0

100-75-50-25-0

100-86-57-29-0
Circuit breaker (compressor and motor), overload protector (compressor and motor), pressure relief pipe, antiphase and phase loss protector, high pressure protector, low pressure protector, built-in temperature protector

Protector(compressor and motor), anti-freezing protection, compressor frequent startup-stop protection, and temperature
sensor failure protection.
Class 1 Armaflex (NBR/PVC)

Thermal insulation material
2-1/2B(65A)

Inlet/outlet pipe for cooling waterPiping

Type

Refrigerant oil

3B(80A)

1B(25A)

Lower water outlet

Refrigerant

2-1/2B(65A)
1-1/4B(32A)

Upper water outlet

R407C/R407H

Factory chargekg

4.5 x 2 + 2.0 x 1

3.0 x 3 + 1.0 x 1

2.5 x 4On-site charging
quantitykg

1.0 x 3

1.5 x 4

2.0 x 4TypeCharging quantity

L/min

3.253 x 2 + 1.774 x 1

POE (Copeland Ultra22cc)
3.253 x 3 + 1.774 x 1

3.253 x 4

Unit static weight

kg

1230

1550

1585

Operating weight

kg

1270

1640

1670

★ 1 The cooling capacity is measured based on the operating conditions in which return air temperature 31 DB/24 WB, and the fan motor heat is not included in the coolingcapacity.
★ 2 Cooling water inlet temperature 38°C.
★ 3 Conditions for heater inlet: inlet air dry-bulb temperature is 10°C, and inlet steam pressure is 0.4 MPa.
★ 4 The humidification capacity is measured based on the operating conditions in which the pressure of saturated steam is 0.035 MPa.
©2015 ShenZhen McQuay