TM

Featuring the

BurnerTested and Listed by

Omni-Test Laboratories, Inc.
Beaverton, Oregon
Report # 028-S-20b-1
ANSI Z21.88, CSA 2.33 MR8,CAN/CGA 2.17-M91• Built-In Direct Vent Fireplace• Natural Gas or Propane• Residential or Mobile HomeWARNING:

Improper installation, adjustment, alteration, service or maintenance can cause
injury or property damage. Refer to this manual. For assistance or additional
information consult a qualified installer, service agency, or the gas supplier.

-

Do not store or use gasoline or other flammable vapors and liquids in the vicinity of this or
any other appliance.

-

Installation must be performed by a qualified installer, service agency or the gas supplier

IF YOU SMELL GAS• Do not try to light any appliance.
• Do not touch any electrical switch; do not use any phone in your building.
• Immediately call gas supplier from a neighbor's phone. Follow the gas supplier's instructions.
• If you cannot reach your gas supplier, call the fire department.

36 DV EFIII Owner’s Manual
Installer: After installation give this manual to the home-owner andexplain operation of this fireplace.

$10.00 Copyright 2005 Travis Ind.

# 100-01160

40509234800 Harbour Pointe Blvd. SW
Mukilteo, WA 98275

Introduction

2
Introduction

We welcome you as a new owner of a Fireplace Xtrordinair gas fireplace. In purchasing a Fireplace
Xtrordinair you have joined the growing ranks of concerned individuals whose selection of an energy
system reflects both a concern for the environment and aesthetics. The Fireplace Xtrordinair is one of
the finest home heaters the world over. This manual will explain the installation, operation, andmaintenance of this fireplace. Please familiarize yourself with the Owner's Manual before operating
your heater and save the manual for future reference. Included are helpful hints and suggestions thatwill make the operation and maintenance of your new fireplace an easier and more enjoyable
experience. We offer our continual support and guidance to help you achieve the maximum benefit
and enjoyment from your heater.

Important Information
No other Fireplace Xtrordinair gas fireplace has thesame serial number as yours. The serial number isbelow and to the left of the gas control valve.
This serial number will be needed in case you require
service of any type.

Model:

36 DV EFIII

Serial Number:
Purchase Date:

To receive full warranty coverage,
you will need to show evidence ofthe date you purchased yourheater. Do not mail your Bill ofSale to us.
We suggest that you attach yourBill of Sale to this page so that you
will have all the information you
need in one place should the needfor service or information occur.

Purchased From:

Travis Industries

Mail your Warranty Card
Today, and Save Your Bill ofSale.

4040708

100-01160

Table of Contents
Introduction

Finalizing the Installation

Introduction & Important Information................2

1 Glass Frame Removal (& installation).............27
2 Log & Coal Installation ................................29
3 Leak Test.................................................31
4 Replace the Glass .....................................31
5 Faceplate Installation .................................31
6 Pilot Adjustment (if necessary).....................31
7 Air Shutter Adjustment (if necessary) ............31
8 Check Flame.............................................32
9 Explain Operation to Home-Owner.................32

Safety Precautions
Safety Precautions ......................................4

Features & Specifications
Features ....................................................6
Installation Options ......................................6
Heating Specifications ..................................6
Dimensions.................................................6

Operation

Installation
Installation Warning......................................7
Packing List................................................7
Additional Items Required for Installation ..........7
Installation Overview ....................................7
Fireplace Placement Requirements..................8
Minimum Framing Dimensions ....................8
Clearances ............................................8
Corner Installations .................................9Raised Fireplaces....................................9Hearth Requirements ....................................10
Facing Requirements ....................................11
Facing Over 1" Thick.....................................11
Facing Detail ...............................................12
Face Dimensions .........................................13
Rectangular Faces .......................................14
Facing and Hearth Examples ..........................14
Mantel Requirements ....................................16
Vent Requirements.......................................17
Altitude Considerations ............................17
Clearances ............................................17
Use of 8” Dia. Pipe ...................................17
Part Numbers for 6-5/8" Dia. Pipe................17
Vent Installation......................................18
Approved Vent Configurations ........................19
Restrictor Position...................................19
Elbows ..................................................19
Measuring Vent Lengths ...........................19
Vertical Term. 0,2 or 4 45° Offsets (6-5/8")....20
Hor. Terminations with 6-5/8" Dia. Vent ........21
Vert. Term. with 2 or 3 Elbows (6-5/8" Dia.)....22
Horizontal Terminations with 8” Dia. Vent......23
Vent Termination Requirements ......................24
Gas Line Requirements .................................25
Fuel ......................................................25
Gas Line Connection................................25
Gas Inlet Pressure ..................................25
Electrical Connection....................................26

Travis Industries

3

Before You Begin .........................................33
Location of Controls .....................................33
Starting The Pilot .........................................34
Starting the Fireplace for the First Time.............35
Turning the Fireplace On and Off .....................35
Adjusting the Flame Height.............................35
Adjusting the Blower Speed............................36
Normal Operating Sounds ..............................36
Normal Operating Odors ................................36

MaintenanceYearly Service Procedure ..............................37
Troubleshooting Table...................................38
How this Fireplace Works...............................39
What Turns the Main Burners On and Off......39
What Prevents Gas Buildup.......................39
Wiring Diagram ............................................40
Replacement Parts List .................................40

Safety Label
Safety (Listing) Label....................................41

Warranty
Warranty ....................................................42

Optional Equipment
LP Conversion Kit ........................................43
Power Heat Duct ..........................................46

Index

4040708

Index.........................................................52

100-01160

Safety Precautions

4• IF YOU SMELL GAS:
* Do not light any appliance* Extinguish any open flame* Do not touch any electrical switch or plug or unplug anything* Open windows and vacate building* Call gas supplier from neighbor's house, if not reached, call fire
department•

This unit must be installed by a qualified installer to prevent the possibility of an
explosion. Your dealer will know the requirements in your area and can inform you of
those people considered qualified. The room heater should be inspected before use
and at least annually by a qualified service person. More frequent cleaning may berequired due to excessive lint from carpeting, bedding material, etc.

•

The instructions in this manual must be strictly adhered to. Do not use makeshiftmethods or compromise in the installation. Improper installation will void the warranty
and safety listing.
Look for this label:•

For LPG only | Pout 11” W.C.
If the label is present, theheater is equipped for LP(propane). If the label isabsent, the heater is equipped
for NG (natural gas).

•

Contact your local building
officials to obtain a permit
and information on any
installation restrictions orinspection requirements inyour area. Notify yourinsurance company of thisheater as well.

• If the flame becomes sooty,
dark orange in color, or
extremely tall, do not
operate the heater. Call
your dealer and arrange forproper servicing.

•

It is imperative that control
compartments, screens, or
circulating air passagewaysof the heater be kept clean
and free of obstructions.
These areas provide the airnecessary for safe
operation.

• Do not operate the heater if
it is not operating properly in
any fashion or if you are
uncertain. Call your dealer
for a full explanation of yourheater and what to expect.

Ok

AA
A
A
AAA

This heater is either approved for naturalgas (NG) or for propane (LP). Burning theincorrect fuel will void the warranty andsafety listing and may cause an extreme
safety hazard. Direct questions about thetype of fuel used to your dealer. Checkthe label and flame adjust knob on thegas control valve.

•

Gas

Travis Industries

Do not store or use gasoline
or other flammable liquids inthe vicinity of this heater.

4040708

?
AA
A
A
AAA
AAAA
A
AAAA
A
AAAA

• Do not operate if any portionof the heater was
submerged in water or if any
corrosion occurs.

100-01160

Safety Precautions

AA
A
A
AAA
AA
AA
AA
AA
AAA
A
AA
A
A
AAA
AA
A
A
AAA

•

AA
AA
AA
AA
A

5

Do not place clothing orother flammable items on ornear the heater. Because
this heater can be controlled
by a thermostat there is apossibility of the heater
turning on and igniting any
items placed on or near it.

• Light the heater using thebuilt-in piezo igniter. Do notuse matches or any otherexternal device to light yourheater.

•

The viewing glass should be
opened only for lighting thepilot or conducting service.

•

Any safety screen or guard
removed for servicing must
be replaced prior tooperating the heater.

instructions are given in thismanual. All other work must
be done by a trained
technician. Don't modify orreplace orifices.

•

Operate the heater
according to the instructions
included in this manual.

•

If the main burners do notstart correctly turn the gas
off at the gas control valve
and call your dealer forservice.

•This unit is not for use withsolid fuel•Do not place anything inside
the firebox (except theincluded fiber logs).

•

If the fiber logs become
damaged, replace with
Travis Industries log set.

•

Do not touch the hot
surfaces of the heater.
Educate all children of thedanger of a hightemperature heater. Youngchildren should besupervised when they are in
the same room as theheater.

•Travis Industries

Instruct everyone in thehouse how to shut gas off tothe appliance and at the gas
main shutoff valve. The gas
main shutoff valve is usuallynext to the gas meter or
propane tank and requires awrench to shut off.

4040708• Never remove, replace,modify or substitute any partof the heater unless• Allow the heater to cool
before carrying out any
maintenance or cleaning.
• The pilot flame must contact
the thermopile andthermocouple (see theillustration to the left). If it
does not, turn the gas
control valve to "OFF" andcall your dealer.

This
Manual

AA
A
A
AAA
36"

• Do not throw this manualaway. This manual has
important operating andmaintenance instructions
that you will need at a latertime. Always follow the
instructions in this manual.

• Keep all furniture or othercombustible items at least
36" away from the front of
the fireplace (this includes
drapes or doors that may
swing within 36" of the frontof the fireplace).

• Travis Industries, Inc.
grants no warranty,
implied or stated, for
the installation or
maintenance of yourheater, and assumes
no responsibility of any
consequential
damage(s).

100-01160

Features and Specifications

6

Features:- Works During Power Outages (millivolt system)- High Efficiency- Optional Thermostat or Remote Control- Realistic "Wood Fire" Look
- Quiet Blower for Effective Heat Distribution- Convenient Operating Controls- Variable-Rate Heat Output- Low MaintenanceInstallation Options:- Residential or Mobile Home
- Straight or Corner Placement- Flush or Recessed Face
- Raised or Floor Hearth- Internal or External Chase- Horizontal or Vertical Vent
- Power Heat DuctNatural Gas
1,200 - 2,250
43,00023,384Up to 79%
72%

Heating Specifications:
Approximate Heating Capacity (in square feet)*
Maximum BTU Input Per Hour
Minimum BTU Output on Low (with blowers on)
Efficiency** (with blowers on)
AFUE (Annual Fuel Utilization Efficiency)*

Propane1200 - 2,250
43,00020,800Up to 80%
73%

Heating capacity will vary with floor plan, insulation, use of Power Heat Duct, and outside temperature.

** Efficiency rating is a product thermal efficiency rating determined under continuous operation
independent of installed system.
Vent has an external diameter of 6-5/8"
The electrical connection ismade in the lower right rear

46-1/4"25-3/4"*3-1/4"

7-7/8"*

corner.

7-7/8"
6-3/4"
3-3/4"

Power Heat Vent
Hook-Up
6-1/4"

1/2" Stand-offs

21-1/2"23"

40"

26-3/4"

Nail Down Plate(used to secure the1"

fireplace to the1"floor)

35-1/4"43"*

1-7/8"

19-5/8"*Weight: 250 Lbs.
* Includes the 1/2" clearance

6-5/8"

Gas Inlet (on both sides)

Travis Industries

4040708

100-01160

Installation(for qualified installers only)

Installation Warnings:
!
!
!
!

!

!
!

Failure to follow all of the requirements may result in property damage, bodily
injury, or even death.
This heater must be installed by a qualified installer who has gone through a
training program for the installation of direct vent gas appliances.
This appliance must be installed in accordance with all local codes, if any; if not, in
U.S.A. follow ANSI Z223.1 and NFPA 54(88), in Canada follow B-149.
In Manufactured or Mobile Homes must confirm with: In USA, Manufactured Home
Construction and Safety Standard, Title 24 CFR, Part 3280; In Canada, CSA Z240.4
and Gas-Equipped Recreational Vehicles and Mobile Housing. This appliance may
be installed in Manufactured Housing only after the home is site located.
The 36DV is designed to operate on natural gas, or propane (LP).
All exhaust gases must be vented outside the structure of the living-area.
Combustion air is drawn from outside the living-area structure.
Notify your insurance company before hooking up this fireplace.
The requirements listed below are divided into sections. All requirements must be
met simultaneously. The order of installation is not rigid – the qualified installer
should follow the procedure best suited for the installation.

Packing List

Additional Items Required

•
•
•
•
•

•
•
•
•

Propane Conversion Kit
Log Set (Log Set, Coals, & Pins)
Flex Tube with Pipe Adapter
Glass Latch Tool (to un-latch glass frame)
Arch Covers (for arched faces only)

Faceplate (gold or black) - Includes attachment screws
Direct Vent (Simpson Dura-Vent Ph. # 800 835-4429)
Gas Line Equipment (shutoff valve, pipe, etc.)
Electrical Equipment (min. 18 gauge, grounded line)

Installation Overview
See the section"Vent Requirements"

See "Power Heat
Vent" in the optional
equipment section.

See the section "Horizontal
Termination Requirements"

See the section"Acceptable Vent Lengths"

Insulation must not be placed
within the 1/2" clearance tothe side and back of thefireplace.

See the section"Electrical Connection"

See the section "Minimum
Framing Dimensions"

Travis Industries

AA
AAA
AAA
AA
AAA
AAA
AA
AAA
AAA
AAA
AA
AA
AAA
AAA
AAA
AA
AA
AAA
AAA
AAA
AA
AA
AAA
AAA
AAA
AA
AA
AAA
AAA
AAA
AA
AA
AAA
AAA
AAA
AA
AA
AAA
AAA
AAA
AA
AAA
AAAAA
Nail
Down
Plate

See the section"Gas Line Installation"

4040708

4-1/2" Min.

Drywall

Non-combustible facing(see the section "Facing
Requirements")
See the section"Mantel Requirements"

See the section"Hearth Requirements"

See the section "Fireplace
Placement Requirements"

100-01160

7

Installation

8(for qualified installers only)

Fireplace Placement Requirements
Minimum Framing Dimensions
A 1/2" clearance is required along the sides and back of the fireplace. The 1/2" stand-offs on the sides
and 6-1/4" stand-offs on the top of the fireplace are designed to separate the fireplace from theframing members. These stand-offs may contact the framing members but no material may be placed
between the stand-offs.

AAAA
A
A
AAAA
AA
AAAA
AA
AA
AAAA
AA
A
AAAA

46-1/2"

NOTE: if venting directly to the rear,
make sure there is a min. 8-5/8" spacecentered behind the fireplace for thewall thimble. If a 90° elbow is useddirectly off of the fireplace, the thimble
will be centered 51-1/4" above thebase of the fireplace.

If using a remote control orthermostat, route the wire to alocation near the gas line (include
an extra 3' length for hookup).

Gas line (3/8" M.P.T. or 1/2" F.P.T.)
should be routed 6-5/8" behind theframing opening and 1-7/8" above
the base of the fireplace (see "GasLine Connection" for details).

Route the electrical line to a positionat the right rear of the fireplace.

19-5/8"43-1/4"
NOTE: If using the power heat vent,allow for the duct passage whenframing the enclosure.

•

Fireplace must be installed on a level surface capable of supporting the fireplace and vent•Fireplace must be placed directly on wood or non-combustible surface (not on linoleum or carpet)•

Due to the high temperature of the fireplace, it should be located out of traffic and away from furnitureand draperies.

•

This heater may be placed in a bedroom. Please be aware of the large amount of heat this applianceproduces when determining a location.

Clearances•

When installed, walls in front of the fireplace must be a minimum 4-1/2" to the side of the faceplate.

•

Fireplace must be placed so that no combustibles are within, or can swing within 36" of the front of thefireplace (e.g. drapes, doors)•

Fireplace must be placed so the vents below and above the glass do not become blocked

Travis Industries

4040708

100-01160

Installation(for qualified installers only)

Corner Installations
A typical 45° installation uses the minimum framing dimensions shown in the illustration below (NOTE:
all clearances still apply).

14-1/2"

AAAAAAAAAAAA
AAA
AAA
AA
AA
AAAA
AAAA
AAAA
A

46-1/4"12-3/4"Fireplace(includes
1/2"
standoffs)

19-5/8"43"

65-1/2"

11-1/4"Raised Fireplaces•

The fireplace (and hearth, if desired) may be placed on a platform designed to support the fireplace(250 Lbs.) and vent.

•The fireplace may not be raised so as to place the ceiling within 24" of the top of the faceplate.

Raised fireplace

Raised fireplace withraised hearth.

RaisedPlatformRaised Hearth
HearthRaisedPlatform

Travis Industries

Nail the nail down plates to the floor(or raised platform)

4040708

100-01160

9

Installation

10(for qualified installers only)

Hearth Requirements
Floor Mounted
Fireplaces
SIDE VIEW
The hearth must tuckunderneath this ledge.

AA
AA
A
AAAAAAAAAAAAAAAAAAAAAAAAAAA
Face

Tile, Marble, Brick, or other

AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA

Non-Combustible

Fireplace

3/8" Thick Tile

Base of Fireplace

1/2" Cement Board

1"

Decorative Trim(may be combustible)

Min. 3/4”
Max. 15/16”

36" Min. for arch face38-1/4" Min. for16” Min.

rectangular face

Cement Board

Hearth Requirement:
Min. 3/4” of non-combustible material (tilewith cement board, marble, etc.)

RaisedFireplaces

AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAA
AAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAA

When the base of thefireplace is raised a

Base of Fireplace

minimum of 3” off of the

Surface of Floor (carpet, etc.)

floor surface, no hearth isrequired.

Make sure to accomodate the floor covering (carpet,
linoleum, flooring, etc.) when determining the height ofFireplace Standthe fireplace stand (i.e. the thicker the carpet, the taller
the fireplace stand).

Travis Industries

4040708

100-01160

Installation

11(for qualified installers only)

Facing Requirements
NOTE: The combustible area above the facing must not protrude more than 3/4" from the facing. If it
does, it is considered a mantel and must meet the mantel requirements listed in this manual.

Ad

WARNING: Do not use adhesive to secure the cement board or facing. The hightemperatures of the fireplace may cause adhesives to emit odors. Use mastic or thin set (orother non-combustible, non-odorous adherent) to attach the facing to the cement board.
NOTE: Screws may be used to secure the cement board to the fireplace. Do not penetrate
the fireplace more than 3/4”

he

siv

e

The fireplace requires a concrete board (orother non-combustible) extending from theheader to the floor and to the framing
members on both sides. Do not use
sheetrock, plywood or other combustible.

AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA

10" Min.

HeaderNon-combustible Facing

Rectangular Face30" Arch face28-1/2" Rectangular face30-3/8" Architectural face

Base ofFireplaceArch Face

Facing Over 1" Thick•

Architectural faces require a
5/8" gap above the face forface installation.

•

If the facing material is over 1"
thick (e.g. brick, river rock),install the facing around theperimeter of the face. You
may wish to make a facetemplate (see the illustration
to the right). If using an archface, you may wish to orderthe optional set-up face:

4-1/2" Min.
(both sides)

36" Arch face38" Rectangular face36-1/4" Architectural face

AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAAA
AAAAAAAAAAAAA
AAAAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAA
The brick facing must meet the same requirements
listed “Facing Requirements” above.

CenterLine

Face TemplateArch Set-Up Face
Part # 98500692••

For rectangular faces, use apiece of plywood cut to thedimensions shown on page
13 (add 1/8" to eachdimension).
Artisan faces vary in size. Use
the face being installed tocreate a template.

Mounting
Holes

4
-3/

”

-3/
16

19

8”

Note: The brick tucks
below the face template.

/2”
4-1

The face template should be 1/8” larger than thefinished face. Attach the template to the fireplace using
the face attachment screws. Then while building theface, use the template to support the face material andensure the facing does not overlap the face.

7/8”

Note: if using a brick hearth, the fireplace will need to be raised to accommodate the 1” gap betwen theface and the base of the fireplace. For 2-1/2” thick brick this works out to approximately 1-5/8”.

Travis Industries

4040708

100-01160

Installation

12(for qualified installers only)

Facing Detail

AAAAA
AAAAA
AAAAA
AAAAA
AAAAA
AAAAA
AAAAA
AAAAA
AAAAA
AAAAA

1-3/8” Rectangular Faces
1/4" Arch Faces
3/8” Architectural Faces

NOTE: The overlap is 1-1/2" along
the top of the face.

AAAAA
AAAAA
AAAAA
AAAAA
AAAAA

Face

Glass
Access Door

1"

1/2"

Air Space

Do not tuck tile underneath the face on the bottom (there
will be a 1/2" air space below the access door). You may
do this on the sides and top, but not on the bottom.

1"

AA
AA

Make sure these shaded areas are faced overwhen using the arched face. Rectangular faces
do not require this area to be faced.

6-3/4"

21-1/2"

AAA
AAA
AAA

23"

26-3/4"1"

1"•

3-3/4"

35-1/4"

To achieve a facing that is flush with the drywall to the side of the fireplace, recess the framing directly
next to the fireplace. See the illustration below.
TOP
VIEW

This 2x4 is recessed 3/8"
to make a flush facing

1/2" Concrete Board

AAAAAAA

1/2" Drywall

1/2" Drywall

1"

Faceplate

Travis Industries

AAA
AAA
AAA
AAA

Fireplace

Fireplace

3/8" Tile

1/2" Concrete Board

1"

Faceplate

4040708

3/8" Tile

The tile overlaps the drywall
for an overlap facing

100-01160

Installation

13(for qualified installers only)

Face Dimensions
Classic Arched(Gold, Black, or Artisan*)Rectangular Bevel Face
(Black or Gold)

Architectural Faces(French Country,
Arts & Crafts,
Art Deco, or Neo-Classical)

5"
Radius = 35”

29"
Access Door

29-3/8”27-1/2”36”
Access Door
38”

36-1/4”* Artisan faces may vary slightly in sizedue to the forging process.
Access Door

Modifying the Face Angle for Rectangular Faces
If using a rectangular face, adjust the face angles at the top corners of the glass (see the illustration
below).
these foura Removescrews from the faceangle.

Phillips
Screwdriver

the face angle up and replaceb Bendthe two screws on the upper section.

Front ofFireplace

AAAAAAAAA
AAAAAAA
AA
AA
AA
AA
AA
Glass

c Straighten the face angle.

AAAAAAAAAAAAAAAAAA
AA

Re-bend the face angle at thed inward location and re-attach thelower portion with one screw.

AAAAAAA
AA
AA
AA
AA
AA
Travis Industries

AAAAAAAAA
AA
A
4040708

100-01160

Installation

14(for qualified installers only)

Facing and Hearth Examples

AA
AA
AA
AA
AA
AA
AA
AA
AA
AA
AAAAAAAAA
AA
AA
AA
AA
AA
AA
AAAAAAAAAAAAAAAAAA
AAAAAAAA
AA
AA
AA

Side View

Face

Fireplace

SUGGESTION:

If using a hearth, make your platform height adimension that will accommodate the size tiles
you are using and the 1" between the base of
the fireplace and the bottom of the face.

1/2" Cement
Board
Wood Sub
Floor

1"

Base of Fireplace3/8" ThickTile

2x4 and Plywood Platform

Three-Dimensional View

Side ofFireplaceFace

1/2" Cement Board& 3/8" Tile
(tucked behind theface)

Access DoorNOTE:
When fully installed, there will be a 1/2"
air space below the access door on theface. Do not block this space (it isrequired for access door opening andair flow).
Note how the tile facing fits behindthe face on the side and top andbutts up to the face on the bottom.

AAAAA
AAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAA
AAA

Base of Fireplace

2x4 and
Plywood
Platform

Tile

Travis Industries

4040708

Cement Board

100-01160

Installation(for qualified installers only)

15

Facing and Hearth Examples (continued)

AA
AA
AA
AA
AA
AA
AA
AAAAAAAAAAAAAAAAA
AAAAAAAASide View

36 DV FireplaceFace

1/2" Cement Board & 3/8" thick tile(tucked behind the face)

3/8" ThickTile

1/2" Cement
Board

1"

Wood Sub
Floor

Base of FireplaceThree-Dimensional View
Face
NOTE:
When hearth installation iscorrectly completed, there will
be a 1/2" air space below theaccess door on the face. Do
not block this air space (it isrequired for access door
opening and proper air flow).

Side ofFireplace

AAA
AAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAA

Note how thetile facing fitsbehind theface on theside and top.

Base ofFireplace

AccessDoor

1/2" Cement
Board

3/8" Tile

Wood Sub Floor

There will be a 1/16"
clearance between the finish
face and the top of the tile on
the hearth.

WARNING: Do not install cement board underneath the fireplace. To do sowould leave a large gap underneath the finish faceplate sides.

Travis Industries

4040708

100-01160

Installation

16(for qualified installers only)

Mantel Requirements•

The combustible area above the facing must not protrude more than 3/4" from the facing. If it does, it
is considered a mantel and must meet the mantel requirements listed in this manual.

Combustible Mantels

Combustible Mantel
Max.
MantelDepth is8”

24
22 ” Min
”M .A
in.
r
Re ch Fa
ct.
c
Fa es
ce
s

30" Arch face28-1/2" Rectangular face30-3/8” Architectural face

Non-Combustible
Mantels

Non-Combustible mantels must maintain a 12"
clearance to the top of the face and be locatedbelow the header -or- maintain a 24" clearance.

Max.
MantelDepth is8”

Non-Combustible Mantel
Header

Mi

n.

12

"

46-1/8"30" Arch face28-1/2" Rectangular face30-3/8" Architectural face

Travis Industries

4040708

100-01160

Installation(for qualified installers only)

17

Vent Requirements!

The vent must maintain the required clearance to combustible materials to prevent a fire (see“Clearances” below). Do not fill air spaces with insulation.

!

The gas appliance and vent system must be vented directly to the outside of the building, and never
be attached to a chimney serving a separate solid fuel or gas-burning appliance. Each direct vent gas
appliance must use it's own separate vent system.

Altitude Considerations
This heater has been tested at altitudes ranging from sea level to 8,000 feet (2,400 M). In this testing we havefound that the heater, with its standard orifice, burns correctly with just an air shutter adjustment.
!

Failure to adjust the air shutter properly may lead to improper combustion which can create a safety hazard.
Consult your dealer or installer if you suspect an improperly adjusted air shutter.

Clearances
Minimum 1” clearance to all combustibles (measured from the outside of the pipe) e x c e p t for the following:
When using 6-5/8" vent, ahorizontal termination, andan elbow directly off the
top of the fireplace, a 2"
clearance is required
above the horizontal
sections (1" to the sideand below).

AAA
AAA

With any verticalvent directly off thefireplace, theclearance is 1".

2" ClearanceAAA
1" Clearance

Max. 3'
Horizontal
Run

Use of 8” Diameter Pipe•

Most venting configurations use 6-5/8” diameter vent. To achieve longer horizontal runs (over 12’)with a horizontal termination, 8” dia. Simpson Duravent type GS Direct Vent may be used. See thesection “Horizontal Terminations using 8” Diameter Vent” for details. Part Numbers are listed below.

Straight Lengths

Terminations

Penetration, Support

1208B
1207B
1206B
1204B
1203B
1202B
1211B
Black

1284
1285
1250

1242
1241
1263
1288

6" Pipe Length, Black
9" Pipe Length, Black
12" Pipe Length, Black
24" Pipe Length, Black36" Pipe Length, Black48" Pipe Length, Black11” to 14-5/8" Adjustable Pipe,

Horizontal Square Termination
Hor. High Wind Termination
Vinyl Siding Stand-off

Elbows
1245B
1290B

45° Elbow, Black90° Elbow, Black

Wall Firestop
Cathedral Ceiling Support Box
Ceiling Fire-stopWall Strap

Adapter (6-5/8” to 8” dia.)
925T

DV GS 6-5/8” to 8” Increaser

Part Numbers for 6-5/8” Diameter Vent•

Use Model GS Direct Vent manufactured by Simpson Dura-Vent only. Follow the installation
instructions included with the vent. For the nearest Simpson Dura-Vent supplier, call (800) 835-4429.
Vent part numbers and descriptions are listed below.

Straight Lengths
908B
907B
906
906B
904
904B
903
903B
902
902B
911B

6" Pipe Length, Black (interior)
9" Pipe Length, Black (interior)
12" Pipe Length, Galvanized
12" Pipe Length, Black (interior)
24" Pipe Length, Galvanized
24" Pipe Length, Black (interior)
36" Pipe Length, Galvanized
36" Pipe Length, Black (interior)
48" Pipe Length, Galvanized
48" Pipe Length, Black (interior)11" to 14 5/8" Adjustable, Black (interior)

Travis Industries

Vent Terminations
981
982
984
950
991

Snorkel Termination (36" rise)(for basement or raisedtermination installations)
Snorkel Termination (14" rise)(for basement or raisedtermination installations)
Horizontal Square Termination
Vinyl Siding Stand-off
High Wind Vertical
Termination

4040708

Elbows990
990B

90• Elbow
90• Elbow, Black (interior)

Penetration, Support
942
941
943
943S
953
963
988

Wall Thimble
Cathedral Ceiling Support Box
Flashing, 0/12 to 6/12 Roof Pitch
Flashing, 7/12 to 12/12 Roof Pitch
Storm Collar
Ceiling Fire-stopWall Strap

100-01160

Installation

18(for qualified installers only)

Vent Installation•

In addition to the requirements below, follow the requirements provided with the vent.

Vertical Termination

Vertical Vent
Requirements
Use a roof flashing and storm collar
whenever passing through the roof
Use a firestop wheneverpassing through a ceiling8-5/8"
or
10"

Maintain a minimum 1"
clearance from vent toany combustible

Minimum framing
for fire stop

Use a support box
on exposed ventUse a firestop wheneverpassing through a wall
8-5/8"or
10"

Horizontal Vent
Requirements

Minimum
Framing forwall thimble

Maintain a minimum 1" clearance (2" insome cases - see "Clearances") fromvent to any combustible

Horizontal Termination•

Slide the vent sections together and turn 1/4 turn until the sections lock inplace.

•

Screws are not required to secure the vent. However, three screws may be
used to secure vent sections together if desired.

•High temperature sealant is recommended at the appliance starter section
connection (use high-temperature silicone or Mill-Pac®).

•If disassembly is required, at time of re-assembly check to see if the ventcreates a tight fit. If it does not, apply high temperature sealant to the joints of
the affected sections.

•

Horizontal sections require a 1/4" rise every 12" of travel•

Horizontal sections require non-combustible support every three feet (e.g.: plumbing tape)

Travis Industries

4040708

100-01160

Installation(for qualified installers only)

19

Approved Vent Configurations
Restrictor Position•

A vent restrictor is built into the appliance to adjust the flow rate of exhaust gases. This ensuresproper combustion for all vent configurations. Depending upon the vent configuration, you may berequired to adjust the restrictor position. The charts for acceptable vent configurations detail thecorrect vent restrictor position.
To Access the Restrictor:
With the face removed andthe fireplace cool, reachabove the firebox.

WARNING: Use a glove to protect
your hand from burns.

To Adjust the Restrictor:
1 Determine the correct restrictor position (see the charts under"Approved Vent Configurations" - the factory position is #1).
2 Lift up the adjustment plate and move it so the correct notch
falls into the slot on the adjustment bracket.
etc. # 2#7#8Adjustment
Plate
This restrictor is in position 7.

Adjustment
BracketTo adjust, lift up on theadjustment plate andpush it back.

This restrictor is in position 1(factory setting).

Elbows•A maximum of
three 90° elbows orfour 45° offsets
may be used. See
the vent
configurations fordetails.
NOTE: one 45°
elbow may be used
between two
horizontal
sections.

Measuring Vent
Lengths

Vent
Horizontal
Run

Elbows add 3" to thelength of the vent system.

3"

Side
View

3"

12-3/8" tallwith 1-1/2"
of overlap

9-5/8"
11-5/8"*Starter
Section1-1/2"

8-3/4" (10-3/4"*)
wide with 1-1/2" to
3-3/8" of overlap

Vent sections overlap
each other by 1-1/2"

1-1/2"
Vent Length(4', 3', etc.)
Vent
Height46-1/4"EXAMPLE:Two 4' lengths are 7' 10-1/2"
long, but when attached to
the vent system add 7' 9" tothe vent height.
* NOTE:All measurements are for 6-5/8" diameter vent except for thosemarked with an asterik (*), which are for 8".

Travis Industries

4040708

Adds 8" to System Height(Total = 9-1/4" Tall)

100-01160

Installation

20(for qualified installers only)

Vertical Terminations with 0, 2, or 4 45° Offsets using 6-5/8” Dia. Vent•

Use 6-5/8” diameter co-axial vent•

A Maximum of Four 45° Elbows May be Used•

10' Minimum System Height (with or without offsets)•

40' Maximum System Height•

12’ 8” Maximum Horizontal Offset

Offset Length
None
1' Section
2' Section
3' Section
4' Section

Vertical
Rise

OffsetLengthHor. Offset
5"
1'
1' 9"
2' 5"
3' 2"

Vert. Rise
1'
1' 7"
2' 4"
3'
3' 8"

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor position.

30 feet25 feet20 feet15 feetRestrictor
Position # 7

NOTE:
Restrictor positions are based upon lab tests. The
ideal restrictor position may vary slightly, especiallywhen the termination is near the demarkation line.

40' (max) 40' (max)

5 feet35 feet35 feet30 feet30 feet25 feet25 feet20 feet20 feet15 feet15 feet10 feet(min.)

10 feet(min.)

Travis Industries

12' 8"(max)

10 feetRestrictor
Position # 1

NOTE:
The maximum offset
lengths, combined, isfour 4' sections.

5 feet35 feet25 feet20 feet15 feet10 feet(min.)

0 feet0 feet4040708

30 feet5 feet0 feet12' 8"(max)

10 feet5 feet0 feet0 feet0 feet40' (max)

NOTE:
Restrictor positions are based uponlab tests. The ideal restrictor position
may vary slightly, especially when thetermination is near the demarkationline.

5 feetNOTE:
The maximum offset lengths,
combined, is four 4' sections.

AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
AAAAAAAAAAA
Restrictor
Position # 7

Restrictor
Position # 1

10 feet(min.)

5 feet0 feet12' 8"(max)

10 feetAAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA
AAAAAAAAAAAA

12' 8"(max)

35 feetFour 45° Offsets

10 feet40' (max)

5 feet0 feetZero or Two 45° Offsets

5 feet•Horizontal
Offset100-01160

Installation

21(for qualified installers only)

10' (max)

The terminationmust fall within
the shaded area
shown in thechart. Use theindicated
restrictor
position.

12' (max)

10 feet0 feetUse a single 90°
elbow (NOTE:
an additional 45°
elbow may be
used on thehorizontal run).

5 feetHorizontal Terminations using 6-5/8” Diameter Vent

AAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAA
AAAAAAAAAA

10' (max)

Use Restrictor
Position #1

5 feet3 foot length (max)

5 feetWarning:
When an elbow is used directly off
the top of the fireplace, a 2"
clearance is required above thevent (1" below and to the sides).

0 feet12' (max)

10 feet5 feet0 feet0 feet

NOTE:• Horizontal sections require a 1/4" rise every 12" of travel.
• Restrictor positions are based upon lab tests. The ideal restrictor position may vary slightly.

Travis Industries

4040708

100-01160

Installation

22(for qualified installers only)

Vertical Terminations with Two or Three 90° Elbows Using 6-5/8” Dia. Vent

40' (max)

35 feet30 feet25 feet20 feet15 feet25'(max)

20 feet15 feet10 feet5 feet0 feet

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor
position.

AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
Restrictor
Position # 7

NOTE:
Restrictor positions
are based upon lab
tests. The ideal
restrictor position
may vary slightly,
especially when thetermination is near ademarkation line.

40' (max)

35 feet30 feet25 feet20 feet15 feetRestrictor
Position # 1

10 feet(min.)NOTE:
Horizontal sections require a
1/4" rise every 12" of travel.

5 feet10 feet(min.)

5 feet0 feet25'(max)

20 feet15 feet10 feet5 feet0 feet0 feet

NOTE:• Horizontal sections require a 1/4" rise
every 12" of travel.

H2

H2

This is considered a horizontal• The maximum vertical height is 40'.
• The maximum horizontal length is 25'.
• One horizontal elbow is allowed. The
horizontal vent length is calculated byadding the length before and after the
elbow (H1 + H2 = horizontal vent length).

This is considered aH1vertical elbow

elbow (it does not matter
whether it turns right or left).

Horizontal length is calculated by adding

It may be a 45° or 90° elbow.

both lengths of horizontal run(Horizontal Length = H1 + H2).

H1

This is considered avertical elbow

Travis Industries

4040708

100-01160

Installation

23(for qualified installers only)

Horizontal Terminations using 8” Diameter Vent

20' (max)

25' (max)

20 feet15 feet10 feet5 feet0 feet

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor
position.

AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAA

20' (max)

Restrictor
Position #7

15 feet15 feetNOTE:
Restrictor positions are based uponlab tests. The ideal restrictor position
may vary slightly.

10 feet10 feetRestrictor
Position #1

5 feet5 feet6-5/8" to 8" dia. Adapter(must be placed directly off the top of
the fireplace - Part # 925T)

0 feetH2

25' (max)

20 feet15 feet10 feet5 feet0 feet0 feetH1

NOTE:
Vertical
Elbow• Horizontal sections require a 1/4" rise every 12"of travel.
• The maximum vertical height is 20'.

Horizontal
Elbow• The maximum horizontal length is 25'.
• One horizontal elbow (45° or 90°) is allowed
when using 8" vent. The horizontal vent length iscalculated by adding the length before and after
the elbow (H1 + H2 = horizontal vent length).

Travis Industries

4040708

100-01160

Installation

24(for qualified installers only)

Termination Requirements (see the illustration below)
A

Minimum 9" clearance from any door or window

B

Minimum 12" above any grade, veranda, porch, deck or balcony

C

Minimum 12" from outside corner walls

D

Minimum 12" from inside corner walls

Roof
Surface11” Min.
6” Min.

E

Minimum 11" clearance below unventilated soffits or roof surfaces
Minimum 18" clearance below ventilated soffits
Minimum 6" clearance from roof eaves
NOTE: Vinyl surfaces require 24"F

Minimum 18" clearance below a veranda, porch, deck or balcony (must have two open sides)

G

Minimum 48" clearance from any adjacent building

H

Minimum 84" clearance above any grade when adjacent to public walkways or driveways
NOTE: may not be used over a walkway or driveway shared by an adjacent building

I

Minimum 48" clearance from any mechanical air supply inlet, 72" for CanadaJ

Minimum 36" clearance above and 48” below and to the sides of non-mechanical air supply inlet

K

Minimum 36" from the area above the meter/regulator (vent outlet)

L

Minimum 36" from the meter/regulator (vent outlet)

Roof
Eaves

M Minimum 12” above the roof line (for vertical terminations)*Note:N

In Canada the vent termination must be a minimum 2' (.6 M) tall and 2' (.6 M)
above any portion of the roof within 10' (3 M) of the vent.

Minimum 24” horizontal clearance to any surface (such as an exterior wall) – for vertical terminations
E
N
M

E
E

A

K
G

J

A
F

H

D

I

C
L
B

NOTE: Measure clearances to the nearest edge of the exhaust hood.

•

Use the vinyl siding standoff (#950) when installing on an exterior with vinyl siding.

•

Vent termination must not be located where it will become plugged by snow or other material•

These clearances meet UMC-1994 and the CNA/CGA-B149 code standards.

Travis Industries

4040708

100-01160

Installation(for qualified installers only)25

Gas Line Requirements!

The gas line must be installed in accordance with all local codes, if any; if not, follow ANSI 223.1 andthe requirements listed below.

!

The fireplace and gas control valve must be disconnected from the gas supply piping during any
pressure testing of that system at test pressures in excess of 1/2 psig. For pressures under 1/2 psig,
isolate the gas supply piping by closing the manual shutoff valve.

!

Leak test all gas line joints and the gas control valve prior to and after starting the fireplace.

Fuel•This fireplace is designed either for natural gas or for propane (but not for both). Check the
sticker on the top of the gas control valve to make sure the correct fuel is used.

Gas Line Connection•

A manual shutoff valve is required for installation (within 3’ of the heater or inside the fireplace). THandle gas cocks are required in Massachusetts in compliance with code 248CMR.

•

Installation must be performed by a qualified installer, service agency or the gas supplier (InMassachusetts a licensed plumber/gasfitter).
The 1" diameter access hole is located 1-7/8" above the base of the fireplace. Cutan "X" in the gasket covering the inlet and insert the gas line through the gasket.
A shutoff valve may beplaced within the fireplace

If the gas line is routed from theright side, bend the flex tube 180°.

13-3/4"

6-1/2"

5-1/2"
3/8" M.P.T to 1/2" O.D. Fitting(Factory installed)
Gas Control Valve-- OR ---- OR -The included
fitting accepts a
3/8" M.P.T. or
1/2" F.P.T.

10" Flex Tube
(shipped with the fireplace - min. bending radius is 3/4")

Gas Inlet Pressure:Standard Input Pressure
Natural Gas

7" W.C. (1.74 kPA)

Propane13" W.C. (2.73 kPA)•

If the pressure is not sufficient, make sure the piping used is large enough, the supply regulator isadequately adjusted, and the total gas load for the residence does not exceed the amount supplied.

•

The supply regulator (the regulator that attaches directly to the residence inlet or to the propane tank)should supply gas at the suggested input pressure listed above. Contact the local gas supplier if theregulator is at an improper pressure.

Travis Industries

4040708

100-01160

Installation

26(for qualified installers only)

Electrical Connection!

Make sure the household breaker is shut off prior to working on any electrical lines.

!

The fireplace must be properly grounded in accordance with local codes (or ANSI/NFPA 70-1987)•

The electrical line must be 14 gauge, and supply 120 Volts at 60 Hz (2 Amps)

1

Follow the directions below to connect power to the fireplace.
Remove the cover from thefireplace junction box.

b

Insert the sheathed cable from the power source throughthis cable clamp. Once the wires are attached, tighten
the clamp to secure the cable.

1/4" NutdriveraStandard
ScrewdriverdReplacethe coverremovedin step "a".

Electrical
Connector
WARNING: Make sure power is
off from the power lead before
conducting any wiring.

c

Attach the common (white), ground (exposed or green) wires, and hot(black) wires from the power source to the electrical connector (included
with the fireplace). Then attach the connector to the fireplace.

NOTE: If using the power heat duct, you may wish
to route the wiring for it at this point. See theinstructions under "Optional Equipment".

Travis Industries

4040708

100-01160

Finalizing the Installation
1

27

Remove the glass frame (and arch covers) following the directions below.
Warning: The appliance must be completely cool before removing the glass.
Note:

If using an arch face, attach the arch covers after re-installing the glass.

Spring PinaOpen the four latches holding the glass
frame in place (start with the bottomtwo) - follow the directions shown to theInsert the 1/4” key
into the springpin.

Top ofFireboxright.

Glass

Twist 1/4 turn.
Glass Frameb

Lift the glass frame up andpull it forward to remove.

NOTE:
You may need to lift
the glass frame
while re-attaching.

Re-Attaching the Glass Frame:a) Hang the glass frame on the firebox.
b) While holding in place, attach the upper latches(follow the instructions to the right in reverse).
c) Lift the glass frame slightly and attach the lower latches.
Arch Covers (both sides)
Glass
Frame

Arch Cover

Glass

Travis Industries

Latch Bracket

The spring pin willdisengage from thelatch bracket,
opening the latch.

The arch covers (includedin the owner's pack) block
light from exiting the scroll
work on arched faces.
The covers hang on theglass frame.
Arch Faces:
Attach arch covers before
installing the face.
Rectangular Faces:
Discard the arch covers.

4040708

100-01160

Finalizing the Installation

28

Glass Frame Removal (continued) - Spring Pin Installation
The spring pin can come loose from the latch assembly. This occurs when it is turned 1/4 turn when it isdisengaged. Follow the directions below to re-install the spring pin if it becomes loose.

To re-install the spring pin, first
insert this end into a 1/4” key.

NOTE: The spring pins
can be installed with theglass frame in place orremoved.

Insert the spring pin into
this bracket with the pinsaligned vertically.

Push in slightly andtwist 1/4 turn.

With this pin horizontal, thespring pin will remain in place.

Travis Industries

4040708

100-01160

Finalizing the Installation

29?

If converting to propane or using the firebacks, do so now before installing the logs (page 43 and 54).

2

Install the log set following the directions below.

Step 1 Install the logs (see the illustration below).
AA
Place the rear log on
the two platforms at

AA
A
A
AA
AAA

the rear of the firebox.

AA
AA
These pins insert
into the holes in
the log.

AA
AA

AA
AA
AA

Place the front logs
on top of the burner.

AA
AA
AA
AA
AA

These bolts insert into theholes in the logs.

Top View

1” to 1-1/2”
space

Do not placelogs overburner holes.

Travis Industries

Note how the front left log isspaced 1/4” to 3/8” off of theburner holes.

4040708

100-01160

Finalizing the Installation

30

Step 2 Install the twigs and ember chunk (see the illustration below).
Place the left and righttwigs as shown.

AA
AA
AA
AA
AA
AA
AA
AA
AA
AA
AA
A
AAAA
AA
AAAA

AA
AA
AA
AA

Place the ember
chunk as shown.

Step 3 Install the embers along the front of the burner (see the illustrations below).
Do not place the embers over the burner holes.
Front View

Side View!

We recommend you purge the gas line at this time (with the glass removed). This allows gas to be
detected once it enters the firebox, ensuring gas does not build up.

3

Turn on the gas to the fireplace. Turn on gas to the heater. Leak test all gas joints prior to starting theappliance. Start the pilot. Start the main burner. Leak test all gas joints again.

Travis Industries

4040708

100-01160

Finalizing the Installation

31

4

Replace the glass frame (and arch covers when using arched faces - see page 27).

5

Install the faceplate following the instructions included with the faceplate.

!

ACID WASH WARNING: Before installing the faceplate, make sure any masonry that has beentreated with acid wash has been properly neutralized (this is used primarily with brick faces). Acid wash(muriatic acid) is used to remove excess mortar. If not properly neutralized with an ammonia solution,
the gold face may develop a permanent tarnish when the acid evaporates over time. Contact yourdealer if uncertain your facing has been properly neutralized.

6

Check the pilot flame to make sure it looks like the illustration below. Adjust the pilot flame ifnecessary.
To adjust the pilot flame, turn this screw (NOTE: if totally

The pilot flame must contact the thermocouple andunscrewed gas will come out of this port). Clockwise

thermopile (see the illustration below). Adjust the pilot up or

lowers the flame while counter-clockwise raises it.

7Standard
Screwdriver

down as necessary.

Let the heater burn for fifteen minutes. Adjust the air shutters, if necessary, to achieve the correct
looking flame (see the illustration below).
•

The air shutter adjusts the amount of air that mixes with the gas before it exits the burner holes.
ADJUSTING THE AIR SHUTTERS
Gas Control Valve
Pushing the control to the left gives theflame less air (making it more orange).
Pushing to the right gives the flame more
air, making it more blue. For fineadjustments use a screwdriver to tap the
air shutter.
NOTE: If the air shutter is all the way

Front Air
Shutter Control

Rear Air
Shutter Control

open, yet the flames remain sooty, shut

NOTE: The logs must be installed correctly to

off gas to the fireplace and contact amonitor the flame while adjusting the air shutter.

qualified gas service technician.

Correct

Not Enough Air

Flames should be blue at theIf the flames are over 14" tall or sooty on

If the flames are all blue andbase, yellow-orange on the top.

the ends, open the air shutter.

short, close the air shutter.

Travis Industries

4040708

Too Much Air

100-01160

Finalizing the Installation

32
8

Turn the flame adjust knob to its highest position - the flames should be approximately 10" tall. Checkthe flame on low position. The flames should burn off of each burner hole. If the heater does not work
correctly, contact your dealer for a remedy.

FINE TUNING THE EMBER-FYRE™

BURNER

Each installation is affected by altitude, vent configuration, and fuel quality. Because of this, the restrictor and air
shutter may need to be fine tuned to each installation. Follow the hints below to fine-tune the burner for
optimum performance and aesthetics.
Restrictor Hints:
Set the restrictor to the position suggested in the vent configuration table (see pages 20-23). Turn the heateron and allow it to reach full temperature (15 min.). If the flames indicate there is excessive draft due to altitude orclimate, you may wish to adjust the restrictor to a more restrictive position (higher number). Active, flickering
short flames are an indication of excessive draft. If the flames lift off of the burner holes, this indicates notenough draft (restrictor is set too high). After adjustments are made the unit must be cooled down to room
temperature and restarted to make sure that the restriction is not so severe that the pilot will drop out when it isrestarted. If the pilot does drop out reduce the restriction until it will operate continuously.
Air Shutter Hints:• For more glow, open the air shutter, however, this will make the flames more blue.
•

For yellow flames, close the air shutter, however, this may create less glow.
Correct Flames

Lifting Flames

Burner

The flames should burn rightoff the top of the burner ports(if they are too blue, adjust
the air control).

Ghosting Flames

Flickering Flames

Burner Ports(holes)Lifting flames indicate
insufficient draft (restrictor
is set too high).

Ghosting flames indicate
insufficient air (restrictor set too
high, air shutter shut down, orother venting error).

AA
AA
A
AA
AA
AA
AAA
AAAA
AA
A
AA
AA
AAA

Flickering, short flames
indicate excessive draft(move air shutter to a higher
position).

Warning: If the vent configuration is installed incorrectly the vent may cause the flames inside the heater to lift or“ghost” – a dangerous situation. Inspect the flames after installation to insure proper performance. If thevent configuration is correct, yet the flames are lifting or ghosting, shut off gas to the heater and contact
the dealer for information on remedying the problem.

9

Give this manual to the home owner and fully explain the operation of this heater.

Travis Industries

4040708

100-01160

Operation

33

Before You Begin!

Read this entire manual before you use your new fireplace (especially the section "Safety
Precautions" on pages 4 & 5). Failure to follow the instructions may result in property damage, bodily
injury, or even death.

Location of Controls - See explanation below
The pilot flame is locatedbelow the rear log.
An instruction card for
operating the fireplaceis attached to theinside of the fireplace
here. Replace it foreasy reference.

AAAAA
AAA
AA
A
AAAAA
AAA
AAAAA
AA
A
AAAAA
AAA
A

Open the access door
to view the controls.
Gas Control Valve
Flame Adjust Knob

MAIN BURNER

Gas Control Knob

ON

HI

LO

BLOWERCONTROL

OFF

On/Off Switch

OFF

PILOT
IGNITER

Pilot Igniter

Blower Knob

Blower Knob

This knob controls the speed of the internal convection blower that pushes
the heated air into the room.

On/Off Switch

This control is used to turn the fireplace on and off.

Pilot IgniterThe pilot igniter is used only to start the pilot. When pressed, it sends anelectrical charge to the pilot assembly. This creates a blue spark directly next
to the pilot, igniting the pilot flame.

Gas Control Knob

This knob is used to control gas to the fireplace and for starting the pilot.
There are three positions, ON, OFF, & PILOT. The pointer to the left of theknob indicates the position this knob is in.

Flame Adjust Knob This knob controls the flame height from low ("LO") to high ("HI"). The pointerabove the knob points to the position this knob is in.

Travis Industries

4040708

100-01160

Operation

34

Starting The Pilot Flamea

The pilot flame is required to ignite the mainburners (it also plays a safety role). It should beleft on once lit. It will stay lit unless the gas
control valve is turned to "OFF". However, thepilot will go out if the gas is shut off, thepropane tank runs out (or low) or if the stove
malfunctions. If the pilot turns off frequently,
call your dealer for information. To start thepilot follow the directions below:

5 minutesb

WARNING:
When lighting or re-lighting thepilot, the glass must be removed(see page 27).
aRemove the glass (see page 27 for details).

b

Push the gas control knob in slightly and turnit to the "OFF" position. The knob will notturn from "ON" to "OFF" unless the knob isdepressed slightly. Wait five minutes to let
any gas that may have accumulated inside
the firebox escape. If you smell leaking gas,follow the directions on the cover "IF YOU
SMELL GAS".

AA
AAA
AAA
AA

PILOT
IGNITERc

30 secondscTurn the gas control knob to the "PILOT"
position and press the knob in, this will allow
gas to flow to the pilot light. Press the
button on the pilot igniter repeatedly until
you see the pilot light.
WARNING:
If the pilot does not light after 15
seconds, release the knob and callyour dealer for service. Do not
attempt to light pilot until service
has been performed.

AA
AAA
AAA
AA

d

?
e

NOTE:
You may wish to remove the log set
to gain a better view of the pilot (seepage 28).
d

Keep the gas control knob depressed for 30
seconds once it is lit.

eRelease the gas control knob. If the pilot
goes out, repeat step C. If the pilot refuses
to stay lit, call your dealer for service. With
the pilot lit, proceed to step “f”.

fReplace the glass.

gTurn the gas control knob counter-clockwise
to "ON". The pilot is now lit and the heater
can be turned on and off.

Travis Industriesfg4040708

100-01160

Operation

35

Starting the Fireplace for the First Time+

Burn the heater at a high setting with the blower off for an extended period (up to 48 hours). This will
cure the painted surfaces. Fumes from the paint curing and oil burning off the steel will occur. This isnormal. We recommend opening a window to vent the room.

+

Condensation may appear on the glass each time you start the fireplace - this is normal.

+

Blue Flames will occur on the fireplace when it first comes on. After fifteen minutes the flames willturn a more realistic yellow and orange color.

?

Certain installations use a remote "wall switch" to turn the fireplace on and off. If this is the case, leave
the ON/OFF switch "ON".

Turning the Fireplace On and Off
After the pilot has been started...
See the instructions included
with the remote for details on
operation.

°F

See the instructions
included with theremote for changing
the battery.

Use this switch toturn the main burner
on and off manually.

Au t

o

Ca Tim
nc e
el

Tim
Se e
t

OM

TE

OF MP
F

F

RO

OF

MI
N

SE
T
TE
MP
TIM
ER

°F

ON

For systems with wall
thermostats, use this switch tocontrol the temperature (rightis hotter, left cooler). Somesystems require the on/off
switch to be on.

!

Do not place any combustible items on top of or directly in front of the fireplace, even temporarily. The
optional thermostat may start the fireplace causing a combustible item to ignite.

?

If the fireplace turns on and off frequently while using the thermostat, you may want to adjust the flame
height down until it produces just enough heat needed.

Adjusting the Flame Height+Your fireplace has an adjustable flame to tailor the look and heat output to your specific needs. It isadjusted by turning the middle dial on the gas control valve.
Flame Height
Adjustment Knob

Index Mark

Turn counter-clockwise to adjust the flame higher, clockwise to lower.

Travis Industries

4040708

100-01160

Operation

36

Adjusting the Blower Speed
The internal blower helps transfer
the heat from the fireplace into theroom. It will not turn on until thefireplace is up to temperature(approximately 10 minutes after
starting). See the illustration below
for instructions on adjusting theblower speed.

OFF

HI

LO
BLOWERCONTROL

Blower Knob
Turn the knob all the way counter-clockwise to turnthe blower off. One click clockwise turns theblower to high speed. Turning the knob clockwisefrom the high position decreases the speed of theblower.

Optional Power Heat Duct
Allow the fireplace to reach normal operating temperature. Then use the wall-mounted rheostat tooperate the blower speed. The blower will automatically shut off after the fireplace cools.

OFF
Turn the dial all
the way counterclockwise until itclicks off.

HIGH

LOW

The high position is
all the way counterclockwise, without
clicking off.

Turn the dial
all the way
clockwise.

Normal Operating Sounds
The appliance will creak withchange of temperature.

BlowerThis heater uses a blower to push heated air into

Pilot Flame

the room. You will hear the sound of air movement

The pilot flame, which remains on,that increases as the speed is increased.

makes a very slight "whisper"sound.
Blower Snap Disk
This part can produce a clicking sound as it turns

Gas Control Valvethe blower on and off.

As the gas control valve is turned on
and off you will hear a dull clicking

Extinction Pops

sound. This is the valve opening up

It is not unusual, especially on Propane (LP) appliances,and shutting down.

to experience a "pop" when the burner is shut off.

Normal Operating Odors
This appliance has several areas that reach high temperatures. Dust or other particles on these areas
may burn and create an odor. This is normal during start-up. You may notice the smell is more acute if
the appliance was left idle for a long period.

Travis Industries

4040708

100-01160

Maintenance

37

Maintaining Your Fireplace's Appearance!

Fingerprints or other marks left on the optional gold surface may become etched in place if they are not wipedclean prior to turning the fireplace on. Clean the gold with denatured alcohol and a soft cloth (with the fireplacecool). Other cleaners may leave a film that may become etched into the gold.

Yearly Service Procedure!

Failure to inspect and maintain the fireplace may lead to improper combustion and a potentially dangerous
situation. We recommend the following procedures be done by a qualified technician.

1

Check the pilot flame. It should touch approximately 3/8" of the top of the thermopile and touch the top of thethermocouple (see illustration below). If it does not, contact your dealer for service.

2

Shut off gas to the fireplace by turning the gas control knob to "OFF" (see step A under "Starting the Pilot" onpage 34). Let the fireplace cool for 15 minutes. Remove the faceplate (see instructions included with face) andglass (see page 27).

3

Remove the log set (NOTE: the logs are very fragile - see page 28). If severely deteriorated, replace.
Check the logs for sooting. A small amount of soot along the bottom of the logs is normal. If excessive sooting
is found, the fireplace will require adjustment. Contact your dealer.

4

Clean the burner (especially the burner holes) and inspect the following:•••

Check for burner pan holes that are cracked, severely warped, or corroded.
Make sure the burner assembly is not warped or damaged.
Check the firebox and area around the pilot to make sure there is no warping or damage.
If any problem is found, discontinue use and contact your dealer for service.
Check the walls and ceiling of the firebox fordeterioration.
Make sure theburner is notwarped or
damaged.

Before Disassembly Check the pilot flame. It
should touch theAAthermocouple andthermopile.

Thermopile
Pilot Hood

Thermocouple

Check the burner holes.

5

Replace the log set. Replace the glass (if the glass is damaged, replace it). Make sure the gasket along theperimeter of the glass contacts the face of the firebox and forms an air-tight seal. If it does not, re-align or
replace the gasket to insure an air-tight seal. Replace the faceplate.

6

Inspect behind the access door. Clean if necessary. Check the gas control valve and gas lines. If damage isfound, discontinue use and contact dealer for service. Clean the air channels and ducts.

7

Start the pilot and turn on the main burner. The flames should be orange/yellow and not touch the top of thefirebox. If the pilot or main burners do not burn correctly, contact your dealer for service. Monitor the blower
operation.

8

Remove any debris or vegetation near the vent termination. Contact your dealer if any sooting or deterioration isfound near the vent termination.

Travis Industries

4040708

100-01160

Maintenance38

Troubleshooting Table
Problem:
Pilot Will Not Light

Main Burners Will Not
Start

Remote Control Does
Not Work

Thermostat Does Not
Work

Fireplace Will Not
Distribute Heat

Possible Cause:

Don't Call for Service
Until You:

A gas shut off valve is turned off

Check all gas shut off valves

The gas control knob isn't turned to "PILOT"

See "Starting the Pilot Light" Step C

The valve control knob isn't pushed in

See "Starting the Pilot Light" Step C

The igniter wasn't pressed repeatedly

See "Starting the Pilot Light" Step C

No Propane in Tank

Check Tank Level

The pilot light has gone out

See "Starting the Pilot Light"

The gas control valve is turned to "PILOT" or "OFF"See "Starting the Pilot Light"

The ON/OFF switch is turned to "OFF"Turn the ON/OFF switch to "ON"The remote control is not working correctly

See the remote control instructions

The thermostat is disconnected or set too low

See "Thermostat Operation"

The pilot light has gone out

See "Starting the Pilot Light"

The gas control valve is turned to "PILOT" or "OFF"See "Starting the Pilot Light"

The ON/OFF switch is turned to "OFF"Turn the ON/OFF switch to "ON"The remote is too far away from the fireplace

Use the remote closer to the fireplace

The remote control receiver is turned "Off"See the remote control instructions

One of the two remote control batteries is deadSee the remote control instructions

The pilot light has gone out

See "Starting the Pilot Light"

The gas control valve is turned to "PILOT" or "OFF"See "Starting the Pilot Light"

The ON/OFF switch is turned to "OFF"Turn the ON/OFF switch to "ON"The thermostat is set too low

See "Thermostat Operation"

The fireplace is not getting electricity

Check the breaker switch

The fireplace is not up to temperature

See "Operating Your Fireplace"

Pilot Goes Out Once A The gas supply has been shut off
Month Or More

Keep the gas supply turned on

The fireplace has just been started

This is normal - see "Starting theFireplace for the First Time"

Improper air shutter adjustment

Adjust Air Shutter - contact yourdealerFlames Are Too Short(Under 6")

The flame height may be turned too low

Turn the flame height to "HI" See "Adjusting the Flame Height"

Thin Layer of Soot
Covers the Glass

The logs or coals are placed incorrectly

See "Log Set Installation andRemoval"Flames Are Too Blue

Improper air shutter adjustment

Adjust Air Shutter - contact yourdealerTravis Industries

4040708

100-01160

Maintenance39

How this Fireplace Works!

This fireplace was designed with safety as the primary concern. Many of the components inside thisfireplace are for safety purposes. Therefore, only certified gas service technicians should service thisfireplace.

What Turns the Main Burners On and Off

When heated, the thermopile
generates electricity (a very small
amount measured in "Millivolts").

This electricity isused to operate themain burners.

The main burners
are switched on and
off using theelectricity generated
by the thermopile.
The ON/OFF switch,
remote control, or
thermostat control
the circuit to the mainburner.

MAIN BURNER

This fireplace uses a millivolt system to control its operation (a millivolt is a very small amount ofelectricity). The thermopile and thermocouple generate electricity when heated by the pilot flame.
This electricity is used to operate the gas valve. Without enough electricity, the gas valve will not turnon. That is why when starting the pilot the gas control knob has to be pressed in long enough for thethermocouple to heat up and generate enough electricity. The thermopile provides power for the
ON/OFF switch, remote control, or thermostat (see the illustration below). Because the thermopile
generates the electricity needed to turn the fireplace on and off, this fireplace can be operated when
the power is out (although the blower will not run).

ON

OFF

What Prevents Gas Buildup+This appliance utilizes a high-technology gas valve in conjunction with a pilot flame to ensure no gas
builds up inside the firebox.

+

The thermocouple (next to the pilot) senses when the pilot flame is lit. If the pilot flame goes out, thisthermocouple no longer generates electricity, causing the gas valve to automatically shut off all gas tothe heater, preventing the pilot from spilling gas into the firebox.

Pilot Flame
The pilot flame is a time-provencomponent that eliminates the possibilityof gas buildup inside the firebox.
Gas ValveThis high-technology valve automaticallyshuts off all gas if it does not receive a signal
from the thermocouple. If any component isdamaged or sensing a malfunction, or if thewiring is damaged, it will shut off all gas.
Thermocouple
The thermocouple generates a small
amount of electricity. If the pilot flame
goes out, the gas valve automaticallyshuts off all gas.

Travis Industries

External Shut Off Valve
This valve is placed on the gas line
to shut off gas to the applianceduring maintenance procedures.

Ceramic Glass
The glass in your heater is the mostdurable glass available. It has beentested to be extremely resistant tobreakage from temperature changes.

4040708

100-01160

Maintenance40
Wiring Diagram
Millivolt Wiring(for gas control valve)Piezo Igniter
Optional
Thermostat

Optional Remote
Control
Thermocouple

Red

AA

Brown
On/Off Switch

Thermopile

Copper Co-Axial
Wire

OrangeSpark Electrode
Pilot Hood

Red
White

120 Volt Wiring

Optional Power Heat Duct

Power Supply

Ground(attached to fireplace)
Ground(green)Ground(green)Common(white)Common(white)Hot(black)Hot(black)RheostatJunction
Box

Green
Green

Power In
Molex
Connector

Optional
Power
Heat Duct
Molex
Connector

White

BlowerJunction Box

Ground(green)Ground(green)Ground(green)Ground(green)Common(white)Common(white)Common(white)Common(white)Hot(black)Hot(black)Hot(black)Hot(black)Grounded
to Blower

White

Heat Duct
BlowerBlack

Blower Snap DiskBlack

Heat Duct
Rheostat

Fireplace
Rheostat

Optional Second Heat
Duct (same rheostat andblower wiring as above)

Ground (green)
Common (white)
Hot (black)

Black

3

Black

7
6
9
1

Fireplace
Blower

White

4
Black

8

RemoteControl
Molex
Connector

9
7

11
Black

Optional Snap Disk

Optional Regulator
Solenoid (24 V. DC)

2

Black

5

Blue
Blue

1
2
4

Gas Control
Valve(millivolt DC)

3
5

Brown

7

6
8

10

9
11

Red

12

Replacement Parts List
BURNER ASS'Y B31 LP NG
CONTROL DOOR TOOL, 36/32 ARTSN
FAN, CONV, G3/G7-10/G14-16/ #FAN, CONV, MOUNT GROMMETS (4)#GLASS SPRING PIN ASBLY
GLASS w/FRAME ASS'Y 36 DV 04
INJECTOR, PILOT - LP (35) #KNOB (PLASTIC), RHEOSTATS #LOG CHUNKS, LS8 - 2001 #LOG SET, LS13 - SIX PIECE #MAGNET w/OUT SHEATH #ORIFICE, BURNER - No. 43 #ORIFICE, BURNER - No. 46 #ORIFICE, BURNER - No. 54 #ORIFICE, BURNER - No. 55
PIEZO IGNITER, ALL GAS UNITS #PILOT ASS'Y, SIT LP, COMPLETE#

Travis Industries

226-20032
210-10381
97300102
93005017
221-22220
224-21009
100-05217
100-04111
90006817
172-00013
100-02801
100-05205
100-05208
100-05213
100-05218
100-05110
93006516

PILOT ASSY, NG - S.I.T. #PILOT ELECTRODE, S.I.T. PILOT#
PILOT HOOD, S.I.T (REMVABLE) #PILOT INJECTR, S.I.T. NG(#62)#
PILOT THERMO-COUPLE, SIT #PILOT TUBE, S.I.T. PILOT ASSY#RHEOSTAT, SQUARE - w/OFF #SETUP FACE, 36DV-A #STOVE PACKSWITCH, ON/OFF - SMALL, GAS #THERMODISC - 120deg NO #VALVE REGULATOR, LP SIT #VALVE REGULATOR, LP SIT - MOD#VALVE REGULATOR, NG SITVALVE REGULATOR, NG SIT - MOD#VALVE, LP DV, S.I.T. '00 & UP#
VALVE, NG - S.I.T. (1.6-3.5) #WIRE HRNS, MAIN - 36 DVXL '00

4040708

100-05403
93006523
93006517
93006508
93006518
93006522
100-00123
98500692
225-10412
98900747
100-00231
100-05504
100-05505
93006500
100-05506
93006507
100-05508
100-00361

100-01160

Travis Industries
Direct Vent
Vented Gas Fireplace Heater

Fireplace Xtrordinair 36 DV XL

The 36 DV XL is designed to operate on natural gas, or propane (LPG). THIS APPLIANCE IS FACTORY SET FOR USE WITH
NATURAL GAS.
For conversion to Propane (LPG) use factory supplied kit. See owner’s manual for information on making these changes.
WARNINGS:
Improper installation, adjustment, alteration, service or maintenance can cause injury or property damage. Refer to the informationin the owner’s and installation manual provided with this appliance. For assistance or additional information consult a qualified
installer, service agency or the gas supplier.
Keep burner and control compartment clean. See installation and operating instructions accompanying appliance.
This appliance must not be connected to a chimney flue servicing a separate solid fuel burning appliance.
This vented gas fireplace heater is not for use with air filters.
CAUTION: Hot while in operation. Do not touch. Severe burns may result. Keep children, clothing, furniture, gasoline and otherliquids having flammable vapors away.
CAUTION: Do not operate this appliance with glass removed, cracked or broken. Replacement of the panel should be done by alicensed or qualified service person.
Only use direct vent systems listed in owner’s manual to vent this appliance to the exterior (direct discharge only without ductconnection).
This appliance must be properly connected to a vanting system in accordance with manufacturer’s installation instructions.
WARNING: Operation of this appliance when not connected to a properly installed and maintained venting system can result in
carbon monoxide (CO) poisoning and possible death.

Vented Gas Fireplace Heater. Not for use with Solid Fuel.

Tested and certified by OMNI-Test Laboratories, Inc. to the combustion performance and construction requirements of ANSI
Z21.88a-2000 and applicable sections of UL 307b.
This appliance must be installed in accordance with local codes, if any; if none, follow National Fuel Gas Code ANSI Z223.1.
Installation in Manufactured or Mobile Homes must conform with Manufactured Home Construction and Safety Standard, Title 24
CFR, Part 3280.
This appliance is only for use with the type of gas indicated on this rating plate and may be installed in an aftermarket,
permanently located, manufactured (mobile) home where not prohibited by local codes. See owner’s manual for details. Thisappliance is not convertible for use with other gases, unless a certified kit is used.

Report No. 028-S-20b-1

Minimum Clearances to Combustibles

4040708N.G.
43,00029,000

L.P. N.G.
Minimum Inlet Pressure (inches W.C.)............. 11.5” 5.5”
Maximum Inlet Pressure (inches W.C.)............ 13” 7”
Manifold Pressure on “HI” (inches W.C.) ........ 11” 3.5”

Mar.

2002

Jan.
Feb.

2000
2001

Manufacture
Date:

Jun.

May

Apr.

Sep.

Aug.

Jul.

Dec.

Nov.

Oct.
10850 117th Pl. N.E. Kirkland, WA 98033

0322

In USA, for altitudes above 2,000 feet, the vent configuration, orifice, or combination of both may need to be changed.
See the owner’s manual for information on making these changes.

This appliance is equipped for installation in USA, 0-2000 ft. (0-610 m).

L.P.
Input Rate on “HI” (BTU/Hr)......... 43,000
Input Rate on “LO” (BTU/Hr) ....... 22,600........................................................

FAN TYPE VENTED CIRCULATOR
Blower Electrical Rating: 115 V., 1.5 Amps, 60 Hz, 150 watts

Hearth Extension in Front - 16” (406mm), 0” (0mm) if Fireplace Raised 3” (76mm)
Hearth Extension to Sides of Faceplate . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 0” (0mm)Sides to enclosure (from stand-offs). . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 0” (0mm)
Faceplate to 8” Deep Mantel - 22” (558mm) for Rectangular Faces, 24” (610mm) for Arched Faces*
Flue Vent . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . See Owner’s Manual* See Owner’s Manual For Additional Mantel Clearances and Options.

Faceplate to Adjacent Wall . . . . . . . . . . . . 4-1/2” (115mm)
Wood Floor Beneath Fireplace . . . . . . . . 0” (0mm)
Back to enclosure (from stand-offs) . . . 0” (0mm)
Top to enclosure (from stand-offs) . . . . . 0” (0mm)

Safety Label
41

The safety (listing) label is adhered to the base of the fireplace near the gas control valve. A copy ofthe safety label is shown below.

100-01160

Limited 7 Year Warranty

42

To register your TRAVIS INDUSTRIES, INC. 7 Year Warranty, complete the enclosed Warranty card and mail it within ten (10) days of the appliancepurchase date to: TRAVIS INDUSTRIES, INC., 4800 Harbour Pointe Blvd. SW, Mukilteo, WA 98275. TRAVIS INDUSTRIES, INC. warrants this gas
appliance (appliance is defined as the equipment manufactured by Travis Industries, Inc.) to be defect-free in material and workmanship to the original
purchaser from the date of purchase as follows:
Check with your dealer in advance for any costs to you when arranging a warranty call.
Mileage or service charges are not covered by this warranty. This charge can vary from store to store.

Years 1 & 2 - COVERAGE: PARTS & LABOR
Burner Assembly:

Gas Control Assembly

Accessories

Burner, Air Shutter Assembly, Main Burner OrificeFirebox Assembly:

Adjustable control valve, millivolt wiring and connectors (located within
the appliance), thermopile, thermocouple, pilot hood, orifices, pilot gasline, piezo ignitor

Cast Fireback, Panels, Faceplate (see “Conditions andExclusions” # 9)

Adjustable Air Restrictor, Pressure Relief Mechanisms, Glass
Frame and Latch

Ceramic GlassElectrical Assembly:
Wiring harness, snap discs, Blower, Blower Rheostat

Glass (breakage from thermal shock)Ceramic Logs
Log Set, Coals, Ember Strip (Steel Fiber)

Exclusions:

Convection Heat Exchanger
Re-Installation Allowance
One-Way Freight Allowance

Paint, Gasketing

Years 3 THROUGH 5 - COVERAGE: PARTS & LABOR
Firebox Assembly:

Convection Heat Exchanger

Adjustable Air Restrictor, Pressure Relief Mechanisms, Glass
Frame and Latch

One-Way Freight Allowance

Exclusions:

Paint, Gasketing, Burner Assembly, Electrical Assembly, Gas Control Assembly, Ceramic Glass, Ceramic Logs, Accessories(Fireback, Panels, Faceplate), Re-Installation Allowance

Years 6 & 7 - COVERAGE: PARTS ONLY
Firebox Assembly:
Adjustable Air Restrictor, Pressure Relief Mechanisms, Glass Frame and Latch

Exclusions:

Paint, Gasketing, Burner Assembly, Electrical Assembly, Gas Control Assembly, Ceramic Glass, Ceramic Logs, Convection Heat
Exchanger, Accessories (Fireback, Panels, Faceplate), Re-Installation Allowance, One-Way Freight Allowance, Labor

CONDITIONS & EXCLUSIONS
1.

This new gas appliance must be installed by a qualified gas appliance technician. It must be installed, operated, and maintained at all times inaccordance with the instructions in the Owner’s Manual. Any alteration, willful abuse, accident, neglect, or misuse of the product shall nullify this warranty.
2.
This warranty is nontransferable, and is made to the ORIGINAL purchaser, provided that the purchase was made through an authorized TRAVIS dealer.
3.
Discoloration and some minor expansion, contraction, or movement of certain parts and resulting noise, is normal and not a defect and, therefore, notcovered under warranty. The installer must ensure the appliance is burning as per the rating tag at the time of installation. Over-firing (operation above thelisted BTU rate) of this appliance can cause serious damage and will nullify this warranty.
4.
The warranty, as outlined within this document, does not apply to the chimney components or other Non-Travis accessories used in conjunction with the
installation of this product. If in doubt as to the extent of this warranty, contact your authorized TRAVIS retailer before installation.
5.
Travis Industries will not be responsible for inadequate performance caused by environmental conditions such as nearby trees, buildings, roof tops, wind,hills or mountains or negative pressure or other influences from mechanical systems such as furnaces, fans, clothes dryers, etc.
6.
This Warranty is void if:a.
The unit has been operated in atmospheres contaminated by chlorine, fluorine or other damaging chemicals.
b.
The unit is subject to submersion in water or prolonged periods of dampness or condensation.
c.
Any damage to the unit, combustion chamber, heat exchanger or other components due to water, or weather damage which is the result of, but not limited
to, improper chimney/venting installation.
7.
Exclusions to this 7 Year Warranty include: injury, loss of use, damage, failure to function due to accident, negligence, misuse, improper installation,
alteration or adjustment of the manufacturer's settings of components, lack of proper and regular maintenance, damage incurred while the appliance is intransit, alteration, or act of God.
8.
This 7 Year warranty excludes damage caused by normal wear and tear, such as paint discoloration or chipping, worn or torn gasketing, corroded or cracked
logs, embers, etc. Also excluded is damage to the unit caused by abuse, improper installation, modification of the unit, drilling of the orifices, or the use offuel other than that for which the unit is configured. Units are shipped for natural gas and must be converted to propane using the included conversion kit.
Confirm fuel configuration with your installer.
9.
Damage to gold or nickel surfaces caused by fingerprints, scratches, melted items, or other external sources left on the gold or nickel from the use ofcleaners other than denatured alcohol is not covered in this warranty.
10. TRAVIS INDUSTRIES, INC. is free of liability for any damages caused by the appliance, as well as inconvenience expenses and materials. Incidental orconsequential damages are not covered by this warranty. In some states, the exclusion of incidental or consequential damage may not apply.
11. This warranty does not cover any loss or damage incurred by the use or removal of any component or apparatus to or from the TRAVIS gas appliancewithout the express written permission of TRAVIS INDUSTRIES, INC. and bearing a TRAVIS INDUSTRIES, INC. label of approval.
12. Any statement or representation of TRAVIS products and their performance contained in TRAVIS advertising, packaging literature, or printed material is notpart of this 7 year warranty.
13. This warranty is automatically voided if the appliance’s serial number has been removed or altered in any way. If the appliance is used for commercial
purposes, it is excluded from this warranty.
14. No dealer, distributor, or similar person has the authority to represent or warrant TRAVIS products beyond the terms contained within this warranty. TRAVISINDUSTRIES, INC. assumes no liability for such warranties or representations.
15. Travis Industries will not cover the cost of the removal or re-installation of hearths, venting or other components.
16.
If for any reason any section of this warranty is declared invalid, the balance of the warranty remains in effect and all other clauses shall remain in effect.
17. This 7 year warranty is the only warranty supplied by Travis Industries, Inc., The manufacturer of the appliance. All other warranties, whether express or
implied, are hereby expressly disclaimed and purchaser’s recourse is expressly limited to the warranties set forth herein.

IF WARRANTY SERVICE IS NEEDED:
1.
2.
3.

4.

If you discover a problem that you believe is covered by this warranty, you MUST REPORT it to your TRAVIS dealer WITHIN 30 DAYS, giving them proof of purchase, the purchase date, andthe model name and serial number.
Travis Industries has the option of either repairing or replacing the defective component.
If your dealer is unable to repair your appliance’s defect, he may process a warranty claim through TRAVIS INDUSTRIES, INC., including the name of the dealership where you purchased theappliance, a copy of your receipt showing the date of the appliance’s purchase, and the serial number on your appliance. At that time, you may be asked to ship your appliance, freight charges
prepaid, to TRAVIS INDUSTRIES, INC. TRAVIS INDUSTRIES, INC., at its option, will repair or replace, free of charge, your TRAVIS appliance if it is found to be defective in material orworkmanship within the time frame stated within this 7 year warranty. TRAVIS INDUSTRIES, INC. will return your appliance, freight charges (years 1 to 5) prepaid by TRAVIS INDUSTRIES,
INC., to your regional distributor, or dealership.
Check with your dealer in advance for any costs to you when arranging a warranty call. Mileage or service charges are not covered by this warranty. This charge can vary from store to store.

Travis Industries

4040708

100-01160

Optional Equipment(for qualified installers only)43

LP Conversion Instructions
Install the conversion kit prior to installing the gas line to ensure proper gas use.
1

Remove the glass (see page 27). Remove the logs and coals (if installed - page 28)2

Remove the burner (see illustration below).
baRemove the firebox floor.

Lift the pilot hood off the pilot
assembly (you may need topull hard to remove).

AA
AA
AA
AA
AA
AAA
AA
AAA
AAA

WARNING:The burner is fragile handle it with care.

cLift the left side of theburner slightly, then slide it
to the left and lift it upwards(lift the burner from below).
AA
AA
AAA
AAA
AAA
AA
AAA
AA
AAA
AAA

AAAAA
AAAAA
AAAAA
AAAAA
AAAAA

AAA
AAA
AAA
AAA
AAA
AAA
AAA

d
Pull the burner forward, outof the firebox.

Burner Replacement:
Make sure the burner is fully seated.
When in place, the pilot flame must aligndirectly above the burner holes.

Replace the pilot hood
after replacing the burner.

Make sure the bolt head on
the bottom of the burnerinserts into this hole.

Slide the air shutters all theway to the right before
installing the burner.

Make sure the mixing tubes
slide onto the orifices.
AA
AA
AA
AA

Mixing Tubes

AAAAA
AAAAA
AAAAA
AAAAA
AAAAA

AA
AA
AA
AA

AAAA
AAAA
AAAA
AAAA
AAAA
AAAA

Travis Industries

NOTE:
Make sure the burner isfully seated. When inplace, the pilot flame
must align directly above
the burner holes.

Orifices
AA
AA
AAA
AA
AAA
AAA
AAA

4040708

100-01160

Optional Equipment

44
3(for qualified installers only)

Follow the directions below to replace the orifices.
a

Slide the air shutters all
the way to the left.

Rear Orifice

AA
AA
AA
AA

Front Orifice

Manifoldbc

Use a 1/2” open end wrench
to unscrew both orifices.

1/2" Wrench

Apply thread sealant to the LP
orifices prior to installation. Use
the chart below to identify thecorrect orifices.
Rear Burner
Orifice

Front Burner
Orifice

Look here for the orifice identification
Front
Rear

LP
#55
#54

NG
#46
#43

Manifold
5/16”

dScrew the LP orifice in so theorifice shoulder protrudes 5/16”(indicating full insertion).

4

Remove the pilot orifice following the instructions below. Replace with the propane pilot orificeaLift the pilot hoodcRemove the orifice and replace with the LP orifice. Screw theorifice all the way in and replace the pilot hood.

off the pilot
assembly.

Orifice Identification:
LP (Propane) Orificeb

Use a hex wrench tounscrew the orifice.

35
35

NG (Natural Gas) Orifice62
5/32" Hex

NOTE: when re-attaching,
this pin lines up with thenotch in the pilot hood.

Travis Industries

4040708

100-01160

Optional Equipment
5

Install the logs andembers.

6

Replace glass andface.

(for qualified installers only)

45aRemove and discard the threescrews using a slotted screwdriverof Torx T-20.

SlottedScrewdriver(or T-20 Torx)b
Remove and discard theregulator, diaphram, springand center post.

7

Remove the regulator
from the front of thegas control valve.
Replace with the
propane regulator,
using the new gasket
and screws included
with the regulator.
NOTE: Leak test
this area after theheater is installed,
gas is connected,
and the mainburner is lit.

cInstall the LP regulator. Use
the screws included with the
LP regulator. Tighten to
approximately 25 Lbs. torque.

SlottedScrewdriver(or T-20 Torx)

NOTE: Make sure theregulator gasket is correctlyaligned before installation.

dPlace the LPlabel on the baseof the fireplacenear the gas
control valve.

9

Make the gas line connection, bleed the gas line (if applicable), start the heater and thoroughly leaktest all gas connections and the gas control valve. Check the pilot. Adjust if necessary.
WARNING:

When lighting or re-lighting the pilot, the glass must be removed (seepage 27).

To adjust the pilot flame, turn this screw (NOTE: if totally

The pilot flame must contact the thermocouple andunscrewed gas will come out of this port). Clockwise
lowers the flame while counter-clockwise raises it.

Travis Industries

thermopile (see the illustration below). Adjust the pilot up orStandard
Screwdriver

4040708

down as necessary.

100-01160

Optional Equipment

46(for qualified installers only)

POWER HEAT DUCT (part # 98500769)
The optional heat duct allows the fireplace to transfer heat to separate locations in the home. One or
two ducts may be used. Installation should take place prior installing drywall.
Warning: This kit must be installed as specified in these instructions. Do not modify any
component.
Warning: Use of any external blower other than the Travis Power Heat Duct Blower will void thewarranty and listing of this appliance and may create a fire hazard.
Note:

The power heat duct must be installed by a qualified service technician.

Note:

Some building codes
may require the use offirestop spacers
whenever the duct
passes from room to
room.

Note:

When routing ducts
through a cold area
(e.g. crawl space) we
recommend insulating
the duct with fiberglass
insulation. If paperbacked insulation isused, the paper can notcontact the duct.

Floor
Boot

Junction Box

Maximum Duct
Length = 20'

Rheostat(with cover plate)
BlowerBox

Use 10” x 3-1/4”
wall stack (duct)when passing
through tightareas.

Duct Adapter(6” Round to 10” x 3-1/4”)
6" Duct
Starter Ring

Grill

Heat Duct
Electrical
WiringWall Adapter(for use on
2 x 4 walls)

Electrical
Source•Determine the route for the heat duct using the illustration below as a guide.

AAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAA
AAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAAA
A
A
A
A
A
A
A
A
A
A
A
A
A
A
A
A
AA A
A
A
A
A
A
A
AAAAAAAAAAAAAAAAA
A
A
A
A
A
AA
AAAAAAAAAAAAAAAAA
A
A
A
A
AA
A
A
A
A
A
A
A
A
A
A
A
A
A
A
A
A A
AAAAAAAAAAAAAAAAA
A
A

NOTE:
Air flow through the duct is affected bylength and number of bends. Keep thelength and number of bends to the minimum
to maximize performance.

Blower Box

When the duct penetrates thefireplace enclosure vertically and the
top of the enclosure is within 36” of
the top of the fireplace, a firestop
spacer that maintains a 1/2”
clearance between all sides of theduct and any combustible materialmust be used.

AA A
A
AA A
A
1/2”

Travis Industries

20’ Maximum
LengthDuct Adapter(6” Round to 10” x 3-1/4” included with the power heatvent kit)

4040708

Co-Axial Vent
(for intake airand exhaust)0” Clearance to
Combustibles

Use 10” x 3-1/4” wall stack(duct) when passing
through tight areas.

100-01160

Optional Equipment•(for qualified installers only)

47

Attach the blower box to the framing or floorboards of the home following the instructions below.

Wall or Ceiling Mounting
Cut a hole between wall
framing members for theblower assembly.

a5-1/4"

AA
AA
AA
AAAA
AA
AA
AAAA
AA
AA

b

Attach the wall mounting
brackets to the blower box.

16"*

Mount the bracket tothese holes for 2 x 4 walls
Mount the bracket tothese holes for 2 x 6 walls* This blower was designed for framing on 16"
centers - construct additional framing if needed.

cSlide the blower, withwires, into the hole cut
in step "a". Attachwith four screws.

AA
AA
AA
AAAA
A
AA
A
AA
A
AAAA
AA
A
AA
A

Floor Mountinga

Cut a hole between floor joists
for the blower box.

b

Attach the floor boot to the blower box with the included screws.

The screws
attach to eitherof these pairs ofholes. Use theupper pair for
thick flooring, thelower pair forthin flooring.

AAAAA
AAAAA
AAAAA
AA
5-1/4"

14"c

Slide the blower into the holecut in step "a". Attach with fourscrews.

Travis Industries

AAAA
AAAA
A
AAAA
A

4040708

100-01160

Optional Equipment

48•(for qualified installers only)

Attach the starter ring to the fireplace following the directions below (use the mostconvenient side).
1/4" Nutdriver
Starter Ring

Remove and discard thecover plate.

Bend the tabs on the bottom of
the starter ring up to lock it inplace.

•

Install the air duct. Each section, when joined, must be attached with three screws and duct tape (U.L.
181A-P or equivalent). Secure the duct if it is in an area where it may sag or become dislodged.

NOTE:

The air duct has a 0” clearance to combustibles.

Secure all ducting
together with screws.
Then seal the seams
with aluminum ducttape (U.L. 181A-P or
equivalent).

Travis Industries

4040708

100-01160

Optional Equipment•(for qualified installers only)

49

AA
A
AA
AA A
A
AA
AA A
A
A

Attach the grill (and wall adapter, if necessary).

Screws(included withthis kit)

Wall Adapter(for use when the blower box
protrudes from the wall primarily on 2 x 4 walls)

Grill

Phillips
Screwdriver

WIRING INSTRUCTIONS
Warning: All wiring should be done by a qualified electrician and shall be in compliance with local
codes and with the current National Electric Code ANSI/NFPA 70 (in the U.S.), or with thecurrent CSC22.1 Canadian Electric Code (in Canada).
Warning: Make sure the fireplace electrical circuit is disabled prior to working on electrical hookup.

Wiring Diagram

Heat Duct
Rheostat

Power Supply

Fireplace

BlowerSnap Disk

Hot(black)Hot(black)Common(white)Common(white)Ground(green)Ground(green)Molex
Connector

Heat Duct
BlowerMolex
ConnectorHot(black)Hot(black)Hot(black)Hot(black)Common(white)Common(white)Common(white)Common(white)Ground(green)Ground(green)Ground(green)Ground(green)RheostatJunction
Box

BlowerJunctionBox

Hot(black)Common(white)Fireplace
BlowerTravis Industries

Fireplace
Rheostat

Optional Second Heat
Duct (same rheostat andblower wiring as above)

Ground(green)4040708

100-01160

Grounded
to Blower

Optional Equipment

50•(for qualified installers only)

Follow the directions below to wire the blower box.

ab

Remove the cover fromthe blower box.

Standard
Screwdriver

Phillips
Screwdriver

Insert sheathed cable through the cable clamp.
After the wires have been connected tighten theclamp to secure the cable.
the hot (black) and common (white) wires to thec Attachleads coming from the wires (use wire nuts).

dSecure the ground wire to the ground stud inside theblower box by tightening the included nut over the
ground wire. Re-attach the cover removed in step"a".

Ground Wire•

Follow the directions below to wire the rheostat. NOTE: There are two types of junction boxes, use
the appropriate junction box for your installation.

aForce the sheathed cable throughone of the locking flaps on thejunction box (repeat for the othercable). Some force is needed.
The flap will lock the cable in place.

From
Blower Boxb

NOTE:Two junction
boxes are included use the best box foryour installation.

Attach the common (white) wires
together. Attach the ground(exposed or green) wires together.
Then attach each of the hot (black)wires from the cables to the two
wires on the rheostat (orientation
does not matter). Carefully packthe wires into the junction box.

c

Attach the cover plate(either white or beige) with
the included screws. Slide
the knob (either white or
beige) over the rheostat
shaft.

Standard
ScrewdriverTo
Fireplace

Travis Industries

4040708

100-01160

Optional Equipment•(for qualified installers only)51

Run the free wire from the rheostat junction box to the fireplace. Follow the directions below toconnect the heat duct circuit to the fireplace.

aRemove the cover from thefireplace junction box.

c1/4" Nutdriver

Note: you may need to loosen this cableclamp to ease removal of the cover plate.

Insert the sheathed cable from the rheostat through acable clamp and push the cable clamp into the knock-out
hole to secure it in place. Once the wires are attached,tighten the clamp to secure the cable.

Standard
ScrewdriverPower
SourceforFireplaceElectrical Connector(included with theheat duct kit)Standard
Screwdriver

MAINTENANCE

e
Replacethe coverremovedin step "a".

To optional second
power heat vent (usethe center knock-out).

b
Pry out and discard
this knock-out.

dAttach the common (white), ground (exposed or green) wires, and hot(black) wires from the cable leading to the rheostat to the molex
connector. Then attach the molex connector to the fireplace.

INSTRUCTIONS

Once a year the grate should be removed and the blower area cleaned. Use a vacuum to clean
around the squirrel-cage blower, being careful not to damage any of the blades.

AA
AA
A
AA
A
AA A
AA AA
A
Phillips
Screwdriver

Travis Industries

Use a vacuum cleaner to remove
any debris from the power ventblower.

Grill

4040708

100-01160

Index52

Approved Vent Configurations..........................18
Adjusting the Blower Speed..............................35
Adjusting the Flame Height ...............................34
Air Shutter Adjustment......................................31
Altitude Considerations.....................................16
Blower Control..................................................35
BTU Input.........................................................5
BTU Output......................................................5
Cap (see vent termination).................................23
Chimney Cap (see vent termination)...................23
Chimney Installation (see Vent Requirements)....16
Clearances.......................................................7
Condensation on Glass.....................................35
Corner Installation.............................................8
Dimensions......................................................5
Dura-Vent (part numbers)..................................16
Elbows.............................................................18
Electrical Connection........................................25
Face Dimensions..............................................12
Face Installation................................................30
Facing Requirements........................................10
Finalizing the Installation....................................26
Floor Protection (see "Hearth Requirements")....9
Framing Dimensions .........................................7
Fuel.................................................................24
Gas Control Valve (Location)..............................32
Gas Inlet Pressure.............................................24
Gas Line Connection ........................................24
Gas Line Install..................................................24
Gas Smell.................................See Inst. on Cover
Glass Installation and Removal ...........................26
Glass, Glass Gasket...........................................26
Hearth Requirements........................................9
Heating Specifications ......................................5
Horizontal Vent Termination Requirements ........23
How this Fireplace Works...................................38
Vent Lengths...................................................18

Travis Industries

Installation Options ...........................................5
Items Required for Installation............................6
Leaking Gas .............................See Inst. on Cover
Listing Information ............................................40
Location of Controls..........................................32
Log Set Installation and Removal .......................27
Maintenance ....................................................36
Mantel Requirements........................................15
Measuring Vent Lengths...................................18
Noise (see Normal Operating Sounds) ...............35
Normal Operating Sounds.................................35
Packing List......................................................6
Pilot Flame Inspection.......................................30
Piping Installation (see Gas Line Install)...............24
Raised Fireplaces .............................................8
Restrictor Position ............................................18
Safety Label.....................................................40
Safety Precautions ...........................................2
Starting The Pilot..............................................33
Starting the Fireplace for the First Time...............34
Thermostat Operation.......................................34
Turning the Fireplace On and Off.......................34
Vent Length (see “Vent Configuration”).............18
Vent Part Numbers ...........................................18
Vent Requirements ..........................................16
Vertical Vent Termination Requirements ............23
Warnings..........................................................2
Warranty...........................................................41
Water on Glass (see Condensation) ...................34
Weight (250 Lbs.).............................................5
What Prevents Gas Buildup...............................38
What Turns the Main Burners On and Off............38
Wiring Diagram..................................................39
Yearly Service Procedure..................................364040708

100-01160