864 See ThroughGreenSmart™
Fireplace
Tested and Listed by

OMNI-Test Laboratories, Inc.
Portland, Oregon
Report # 028-F-84-5
ANSI Z21.88b-2003•

Built-In Direct Vent Fireplace•

Natural Gas or Propane•

Residential or Mobile HomeWARNING:

If the information in these instructions is not followed exactly, a fire or
explosion may result causing property damage, personal injury or loss oflife.
- Do not store or use gasoline or other flammable vapors and liquids in the vicinity of thisor any other appliance.
WHAT TO DO IF YOU SMELL GAS• Do not try to light any appliance.
• Do not touch any electrical switch; do not use any phone in your building.
• Immediately call gas supplier from a neighbor's phone. Follow the gas supplier's
instructions.
• If you cannot reach your gas supplier, call the fire department.
- Installation and service must be performed by a qualified installer, service agency or thegas supplier.
This appliance may be installed in an aftermarket permanently
located, manufactured home (USA only) or mobile home, where
not prohibited by local codes.
This appliance is only for use with the type(s) of gas indicated on
the rating plate. A conversion kit is supplied with the appliance.

Installation Manual
Installer:

After installation give this manual to the homeowner and explain operation of this heater.

© Copyright 2009, T.I.

$10.00100-01217_000

4090507

www.travisproducts.com

4800 Harbour Pointe Blvd. SW
Mukilteo, WA 98275

2

Introduction
Overview
This manual details the installation requirements
for the 864 See Through (ST) GS fireplace. For
operating and maintenance instructions, refer tothe 864 ST GS Owner's Manual (part # 10001218).

Listing Details
This appliance was listed by OMNI Test Labs to
ANSI Z21.88 - report # 028-F-84-5. The listing label
is attached to the appliance near the gas control
valve. A copy is shown to the right.

IAS (ICBO) Approval
This appliance was listed by OMNI Test Labs - IAS# TL130.

Massachusetts Approval
This manual has been submitted to the
Massachusetts Board of State Examiners of
Plumbers and Gas Fitters

National Fireplace Institute© Travis Industries

4090507100-01217_000

Table of Contents
Introduction

Installation (continued)

Overview ............................................................................. 2
Listing Details ...................................................................... 2

Safety Precautions
Safety Precautions .............................................................. 4

Features and Specifications
Features .............................................................................. 6
Installation Options.............................................................. 6
Heating Specifications ......................................................... 6
Dimensions ......................................................................... 6

Installation
Packing List ......................................................................... 7
Additional Items Required ................................................... 7
Recommended Installation Procedure ................................ 7
Side Standoff Installation .................................................... 7
Massachusetts Requirements ............................................. 8
Converting the Fireplace to Side Vent Configuration .......... 9Fireplace Placement Requirements .................................... 11
Clearances ...................................................................... 11
Raised Fireplaces ............................................................ 11
Min. Framing Dims. - Rear Vent Configuration ...........................12
Nailing Brackets .............................................................. 13
Gas Line Requirements ...................................................... 14
Fuel ................................................................................. 14
Gas Line Connection ....................................................... 14
Gas Inlet Pressure ........................................................... 14
Gas Line Location............................................................ 14
Electrical Connection (required) .......................................... 16
Optional Wall Switch or Thermostat Installation .................. 17
Vent Requirements ............................................................. 18
Vent Clearances .............................................................. 18
Altitude Considerations.................................................... 18
Approved Vent ................................................................. 19
Vent Installation ............................................................... 19
Approved Vent Configurations ............................................ 20
Restrictor Position ........................................................... 20
Exhaust Restrictor Adjustment ........................................ 20
Intake Restrictor Adjustment ........................................... 21
Diffuser Plate Adjustment ................................................ 22
Rear Vent Config. W Horizontal Term. (no vertical rise) ..... 23
Rear Vent Config. W Horizontal Term. (w vertical rise) ....... 24
Side Vent Configuration with Vertical Termination .............. 25
Top Vent Configuration with Horizontal Termination ........... 26
Top Vent Configuration with Vertical Termination ............... 27
Termination Requirements .................................................. 28© Travis Industries

3

Hearth Requirements .......................................................... 29
Facing Requirements .......................................................... 30
Drywall Installation .......................................................... 30
Facing Overview ............................................................. 31
Optional Faceplates – Sizing Chart ................................. 31
Thin Facing Installation ................................................... 32
Thick Facing Installation .................................................. 34
Thick Facing Installation with FPX Arched Faces............ 35
Mantel Requirements .......................................................... 37

Finalizing the Installation
Steps for Finalizing the Installation ..................................... 38
Air Shutter Adjustment .................................................... 39
Glass Frame Removal and Installation ............................... 40
Log Set Installation ............................................................. 42
LP Conversion Instructions ................................................. 52

Optional Equipment
Fireback Installation ............................................................ 55
Grill Installation ................................................................... 57
Extra Room Power Heat Duct ............................................. 58
Andiron Installation ............................................................. 59
GreenSmart™ Remote Control Installation ......................... 60

Index
Index ................................................................................... 724090507100-01217_000

4Safety Precautions
Safety Warnings:•

Failure to follow all of the requirements may result in property damage, bodily injury, or even death.

•

This unit must be installed by a qualified installer to prevent the possibility of an explosion.

•

This appliance must be installed in accordance with all local codes, if any; if not, in U.S.A. follow
ANSI Z223.1 and NFPA 54(88).

•

A manufactured home (USA only) or mobile home OEM installation must conform with the
Manufactured Home Construction and Safety Standard, Title 24 CFR, Part 3280, or, when such astandard is not applicable, the Standard for Manufactured Home Installations, ANSI/NCSBCS
A225.1, or Standard for Gas Equipped Recreational Vehicles and Mobile Housing, CSA Z240.4. Thisappliance may be installed in Manufactured Housing only after the home is site located.

•

All exhaust gases must be vented outside the structure of the living-area. Combustion air is drawn
from outside the living-area structure. The venting must not be connected to a chimney flue serving aseparate solid-fuel burning appliance.

•

Notify your insurance company before hooking up this fireplace.

•

The room heater should be inspected before use and at least annually by a qualified service person.
More frequent cleaning may be required due to excessive lint from carpeting, bedding material, etc.

•

The instructions in this manual must be strictly adhered to. Do not use makeshift methods orcompromise in the installation. Improper installation will void the warranty and safety listing.

•This heater is approved for use with natural gas (NG) or propane (LP). Burning the incorrect fuel willvoid the warranty and safety listing and may cause an extreme safety hazard. Direct questions about
the type of fuel used to your dealer. Check the label and flame adjust knob on the gas control valve.

•

Contact your local building officials to obtain a permit and information on any installation restrictions
or inspection requirements in your area.

•

If the flame becomes sooty, dark orange in color, or extremely tall, do not operate the heater. Call
your dealer and arrange for proper servicing.

•

It is imperative that control compartments, screens, or circulating air passageways of the heater be
kept clean and free of obstructions. These areas provide the air necessary for safe operation.

•

Do not operate the heater if it is not operating properly in any fashion or if you are uncertain. Call
your dealer for a full explanation of your heater and what to expect.

•

Do not store or use gasoline or other flammable liquids in the vicinity of this heater.

•

Do not operate if any portion of the heater was submerged in water or if any corrosion occurs.

•

Do not place clothing or other flammable items on or near the heater. Because this heater can becontrolled by a thermostat there is a possibility of the heater turning on and igniting any items placedon or near it.

•

Light the heater using the built-in igniter. Do not use matches or any other external device to lightyour heater.

•

Never remove, replace, modify or substitute any part of the heater unless instructions are given in thismanual. All other work must be done by a trained technician. Don't modify or replace orifices.

•

The viewing glass should be opened only for conducting service.

•

Any safety screen or guard removed for servicing must be replaced prior to operating the heater.

© Travis Industries

4090507100-01217_000

Safety Precautions

5

Safety Warnings (continued):•

Allow the heater to cool before carrying out any maintenance or cleaning.

•

Operate the heater according to the instructions included in this manual.

•

If the main burners do not start correctly turn the gas off and call your dealer for service.

•

This unit is not for use with solid fuel.

•Do not place anything inside the firebox (except the included fiber logs).

•

If the fiber logs become damaged, replace with Travis Industries log set.

•

Do not throw this manual away. This manual has important operating and maintenance instructions
that you will need at a later time. Always follow the instructions in this manual.

•

Do not touch the hot surfaces of the heater. Educate all children of the danger of a high-temperature
heater. Young children should be supervised when they are in the same room as the heater.

•

Due to the high temperature, the heater should be located out of traffic and away from furniture anddraperies.

•

Instruct everyone in the house how to shut gas off to the appliance and at the gas main shutoff valve.
The gas main shutoff valve is usually next to the gas meter or propane tank and requires a wrench to
shut off.

•Travis Industries, Inc. grants no warranty, implied or stated, for the installation or
maintenance of your heater, and assumes no responsibility of any consequential damage(s).

© Travis Industries

4090507100-01217_000

6Features and Specifications

Installation Options•

Residential or Mobile Home•Internal or External Chase•

Flush or Recessed Face•

Horizontal or Vertical Vent•

Raised or Floor Placement•

Bedroom Approved

Heating Specifications
Approximate Heating Capacity (in square feet)*
Maximum BTU Input Per Hour*

Natural Gas

PropaneUp to 1,500 (139 sq. M)

Up to 1,500 (139 sq. M)

37,500 (39.5 MJ)

37,500 (39.5 MJ)

Heating capacity will vary with floor plan, insulation, and outside temperature.

Dimensions
38-1/4"972mm
Top Vent Configuration
39-1/8"994mm

8" (203mm) Diameter Vent

4-3/8"
111mm
41-1/2"1054mm3-3/8"
86mm

38-1/4"972mm

Side Vent Configuration
35-1/4"8" (203mm) Diameter Vent

895mm
37"
940mm

33-7/8"860mm

Lifting Handle Tabs

m
1m
04
1
"
41

These tabs may be
used in conjuction withthe lifting handles(98500711) - make sure
to use the required
adapters (250-01038)© Travis Industries

Ba
ck

mm

18

1
"1

44

24"
610mm

ht
Rig

ft

Le

Fro

nt

1" 25mm
Weight: 310 Lbs (140.7 kg)

4090507100-01217_000

Installation (for qualified installers only)

7

Packing List
•
•
•
•

•
•
•

Propane Conversion Kit
Log SetFirestop (sku 93006094)
Right Side Standoffs (2)Wall Switch, Cover Plate, and Wire
4 AA Batteries, 1 9-Volt Battery
Insulation for Side Vent Conversion

Additional Items Required
•
•

•
•

Direct Vent
Gas Line Equipment (shutoff valve, pipe, etc.)
Electrical Equipment (min. 14 gauge, grounded line)
Two Grill Kits and/or Faces

Recommended Installation Procedure
•
•
•
•
•
•
•
•
•
•
•

Prepare the framing, making sure to leave the area around the fireplace open (see page 12). Make sure to allow for ventinstallation and facing depth.
Place the fireplace into position.
Install the vent, gas line and electrical hook-up.
Finalize the framing around the fireplace.
Secure the fireplace to the framing.
Install the wall switch (see page 17) or thermostat (if applicable).
Install the drywall.
Install the hearth (if applicable).
Install the facing (if applicable).
Install the mantel (if applicable).
Finalize the installation (see page 38) and install the grill or face.

Side Standoff Installation
The two right-side standoffs included with thisfireplace are attached to the fireplace prior toplacing the fireplace into position. These standoffs
are not required for safety purposes. Their purpose
is to center the fireplace in the framed opening.
Attach the right side standoffs to the fireplace asshown below. Remove the five screws on the sideof the fireplace, position the standoff, and secure.
NOTE: The side standoffs have obround holes thatallow for the standoff to be adjusted fordrywall of ½” or 5/8” thickness. See“Nailing Brackets” on page 13.

Framing Notes
The framing dimensions included in this installation manual have been revised to include the extra 1-1/2”
needed for the right standoffs to install correctly (44” width). If the fireplace opening has been framed to thedimensions listed in the previous version of the installation manual (42-1/2” width), the right side standoffs
may be excluded. In this type of installation, the center of the glass will not be located in the center of theframed opening. The center of the glass will be ¾” from the center of the framing.
© Travis Industries

4090507100-01217_000

8Installation (for qualified installers only)

Massachusetts Requirements
NOTE: The following requirements reference various Massachusetts and national codes not contained in this document.

Requirements for the Commonwealth of Massachusetts
For all side wall horizontally vented gas fueled equipment installed in every dwelling, building or structure used in whole or inpart for residential purposes, including those owned or operated by the Commonwealth and where the side wall exhaust venttermination is less than seven (7) feet above finished grade in the area of the venting, including but not limited to decks andporches, the following requirements shall be satisfied:
Installation of Carbon Monoxide Detectors
At the time of installation of the side wall horizontal vented gas fueled equipment, the installing plumber or gasfitter shallobserve that a hard wired carbon monoxide detector with an alarm and battery back-up is installed on the floor level where thegas equipment is to be installed. In addition, the installing plumber or gasfitter shall observe that a battery operated or hard
wired carbon monoxide detector with an alarm is installed on each additional level of the dwelling, building or structure servedby the side wall horizontal vented gas fueled equipment. It shall be the responsibility of the property owner to secure theservices of qualified licensed professionals for the installation of hard wired carbon monoxide detectors.
In the event that the side wall horizontally vented gas fueled equipment is installed in a crawl space or an attic, the hard wired
carbon monoxide detector with alarm and battery back-up may be installed on the next adjacent floor level.
In the event that the requirements of this subdivision can not be met at the time of completion of installation, the owner shallhave a period of thirty (30) days to comply with the above requirements; provided, however, that during said thirty (30) day
period, a battery operated carbon monoxide detector with an alarm shall be installed.
Approved Carbon Monoxide Detectors
Each carbon monoxide detector as required in accordance with the above provisions shall comply with NFPA 720 and be
ANSI/UL 2034 listed and IAS certified.
Signage
A metal or plastic identification plate shall be permanently mounted to the exterior of the building at a minimum height of eight(8) feet above grade directly in line with the exhaust vent terminal for the horizontally vented gas fueled heating appliance orequipment. The sign shall read, in print size no less than one-half (1/2) inch in size, “GAS VENT DIRECTLY BELOW. KEEP
CLEAR OF ALL OBSTRUCTIONS”.
Inspection
The state or local gas inspector of the side wall horizontally vented gas fueled equipment shall not approve the installation
unless, upon inspection, the inspector observes carbon monoxide detectors and signage installed in accordance with theprovisions of 248 CMR 5.08(2)(a)1 through 4.
Exemptions
The following equipment is exempt from 248 CMR 5.08(2)(a)1 through 4:• The equipment listed in Chapter 10 entitled “Equipment Not Required To Be Vented” in the most current edition of NFPA 54
as adopted by the Board; and• Product Approved side wall horizontally vented gas fueled equipment installed in a room or structure separate from thedwelling, building or structure used in whole or in part for residential purposes.

MANUFACTURER REQUIREMENTS
Gas Equipment Venting System Provided
When the manufacturer of Product Approved side wall horizontally vented gas equipment provides a venting system design or
venting system components with the equipment, the instructions provided by the manufacturer for installation of the equipment
and the venting system shall include:• Detailed instructions for the installation of the venting system design or the venting system components; and• A complete parts list for the venting system design or venting system.
Gas Equipment Venting System NOT Provided
When the manufacturer of a Product Approved side wall horizontally vented gas fueled equipment does not provide the partsfor venting the flue gases, but identifies “special venting systems”, the following requirements shall be satisfied by the
manufacturer:• The referenced “special venting system” instructions shall be included with the appliance or equipment installation
instructions; and• The “special venting systems” shall be Product Approved by the Board, and the instructions for that system shall include aparts list and detailed installation instructions.
A copy of all installation instructions for all Product Approved side wall horizontally vented gas fueled equipment, all venting
instructions, all parts lists for venting instructions, and/or all venting design instructions shall remain with the appliance orequipment at the completion of the installation.
See Gas Connection section for additional Commonwealth of Massachusetts requirements.

© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

9

Top Vent or Side Vent Configuration
This appliance is shipped in the top vent configuration. To change to the side vent configuration, follow thedirections below.
NOTE: the vent configuration affects several aspects of installation (framing, maximum vent rise, maximum ventrun). Make sure the vent configuration is correct prior to installation. You may wish to configure the diffuser whenchanging the vent configuration.

Converting theFireplace to Side
Vent
Configuration

Remove the back plate on
the fireplace.

NOTE: Use a magnetic-tipped
nutdriver on these screws take care to prevent thescrews from falling into thefireplace.

Remove the flue assembly.

Tuck the two 24" (610mm) pieces of
insulation into the area between theexhaust manifold and fireplace can.
WARNING: Failure to properly
place the insulation will void thewarranty and create a safety
hazard.

© Travis Industries

4090507100-01217_000

10Converting theFireplace toSide Vent(continued)

Installation (for qualified installers only)

Re-attach the flue assemblyin the side position.

Tuck the two 20" (508mm) pieces of
insulation into the area above theexhaust manifold and fireplace can.
Note how the insulation is folded inhalf and covers the entire area above
the exhaust manifold (see illustration
below).
WARNING: Failure to properly
place the insulation will void thewarranty and create a safety
hazard.

Re-attach the back plate to the
top of the fireplace.

NOTE: Make sure the flange on
the back plate tucks between thefireplace and the flue assembly.

© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

11

Fireplace Placement Requirements•

Fireplace must be installed on a level surface capable of supporting the fireplace and vent.

•Fireplace must be placed directly on wood or non-combustible surface (not on linoleum or carpet).

•This heater may be placed in a bedroom. Please be aware of the large amount of heat this applianceproduces when determining a location.

•

Fireplace must be installed in a room with a minimum ceiling height of 84” (2134mm).

Clearances•

The fireplace requires a ½” (13mm) clearance from the left side of the fireplace to the framing members. No
material (insulation, framing, etc.) may be placed into this area.

0" (0mm) clearance on

1/2" (13mm)
Clearnce on left
side offireplace.

right side of fireplace.
NOTE: right sidestandoff is optional.

•

When installed, walls in front of the fireplace must be a minimum 1" (25mm) to the side of the fireplace. Only
one side wall is allowed within 12” (305mm) of the side of the fireplace.

•Due to the high temperature, the heater should be located out of traffic and away from furniture anddraperies.

•

Fireplace must be placed so the vents below and above the glass do not become blocked.

Raised Fireplaces•

The fireplace (and hearth, if desired) may be placed on a platform designed to support the fireplace (310 Lbs.
140.7 Kg) and vent.

Min. 42" (1067mm)
Fireplace Enclosure
HeightPlatform

Optional Raised Hearth(see "Hearth Requirements" for details)© Travis Industries

4090507100-01217_000

12Installation (for qualified installers only)

Minimum Framing Dimensions – Top or Side Vent Configuration

Minimum 42”(1067mm)
Fireplace Enclosure Height

NOTE:
The shaded framing must be
installed after placing the fireplacein position.
The framing above the fireplaceinterferes with the top of the fireplace.
If using the side vent configuration, do
not install the framing to the left side
(shown in light gray).
38-1/2"978mm

44"1118mm

23" *
584mm

Le

ck

ft

Ba
nt

Fro

© Travis Industries

Rig

ht

* The 23" (584mm) dimension is based upon 1/2" (13mm)
drywall around the perimeter of the fireplace on both sides. If
using thicker drywall (or other facing), you will need to adjust thisdimension.

4090507100-01217_000

Installation (for qualified installers only)

13

Nailing Brackets
There are eight nailing brackets on the front and back of the fireplace.
Bend the tabs out to position the nailing brackets. Once in place, nail orscrew the nailing brackets to the framing.

WARNING: Make sure thefireplace is square and plumbwhen placed in the framing.
Measured corner-to-corner, thefireplace should be square(approx. 54-7/8"or 1394mm foreach dimension). Use shims toinsure the fireplace is square.

NOTE: Additional nailing brackets areprovided along the base of thefireplace. Use these brackets if notusing the front brackets.
NOTE: The side standoffs haveobround holes that allow for the
standoff to be adjusted for drywall of
1/2" or 5/8".
NOTE: You may need to bend thetabs out on one side then slide thefireplace out to bend the tabs out on
the opposite side

TOP VIEW
Framing
Nailing Bracket

Fireplace

Drywall© Travis Industries

4090507100-01217_000

14Installation (for qualified installers only)

Gas Line Requirements
MASSACHUSETTS INSTALLATIONS - WARNING:
THIS PRODUCT MUST BE INSTALLED BY A LICENSED PLUMBER OR GAS FITTER WHEN INSTALLED WITHIN THE
COMMONWEALTH OF MASSACHUSETTS.
OTHER MASSACHUSETTS CODE REQUIREMENTS:•

Flexible connector must not be longer than 36 inches.

•

Shutoff valve must be a “T” handle gas cock.

•

Only direct vent sealed combustion products are approved for bedrooms or bathrooms.

•

Fireplace dampers must be removed or welded in the open position prior to the installation of a fireplace insert or gas log.

•

A carbon monoxide (CO) detector is required in the same room as the appliance.

•

The gas line must be installed in accordance with all local codes, if any; if not, follow ANSI 223.1 and therequirements listed below.
The fireplace and gas control valve must be disconnected from the gas supply piping during any pressure
testing of that system at test pressures in excess of 1/2 psig (3.5 kPA). For pressures under 1/2 psig (kPA),
isolate the gas supply piping by closing the manual shutoff valve.
Leak test all gas line joints and the gas control valve prior to and after starting the fireplace.

•
•

Fuel
•

This fireplace is designed either for natural gas or for propane (but not for both). Check the sticker on the top of the gas
control valve to make sure the correct fuel is used.

Gas Line Connection•

Installation must be performed by a qualified installer, service agency or the gas supplier (In Massachusetts a licensed
plumber/gasfitter).
Standard Input Pressure

Gas Inlet Pressure
Natural Gas
Propane••7" W.C. (1.74 kPA)
13" W.C. (2.73 kPA)

If the pressure is not sufficient, make sure the piping used is large enough, the supply regulator is adequately adjusted,
and the total gas load for the residence does not exceed the amount supplied.
The supply regulator (the regulator that attaches directly to the residence inlet or to the propane tank) should supply gas at
the suggested input pressure listed above. Contact the local gas supplier if the regulator is at an improper pressure.

© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)15

Gas Line Location
Right Side Gas Inlet (preferred)
A 2" (51mm) by 3" (76mm) opening islocated behind the gas inlet cover plate. It iscentered 3" (76mm) above the base of thefireplace.

A 8" (203mm) flex tube and shutoff
valve is included with the fireplace.
The shutoff valve accepts a 1/2"MPT.

9-1/4"
235mm

9"
229mm

The gas inlet is located 1-1/4" (32mm)
above the base of the fireplace.

You may remove this cover plate to install the gas line. The
cover plate has a 7/8" (22.2mm) diameter hole (covered witha push plug) in line with the gas inlet on the gas control
valve. By rotating the plate 180° the hole may be re-located.
You may also secure the plate in a customized location using
the self-drilling screws.

Left Side Gas Inlet
An additional 2" (51mm) by 3" (76mm)
opening is located the left side. It is centered3" (76mm) above the base of the fireplace.

A 8" (203mm) flex tube and shutoff
valve is included with the fireplace.
You may wish to use a 24" (610mm)
or 36" (914mm) flex tube. The shutoff
valve accepts a 1/2" MPT.

5-3/8"
137mm

You may remove this cover plate to install thegas line. The cover plate has a 7/8" (22.2mm)
diameter hole (covered with a push plug) in linewith the gas inlet on the gas control valve. Byrotating the plate 180° the hole may be relocated. You may also secure the plate in acustomized location using the self-drillingscrews.

© Travis Industries

4090507100-01217_000

16Installation (for qualified installers only)

Electrical Connection (required)•

The electrical line to the grounded receptacle inside the fireplace must be installed by a qualified installer andmust meet all local codes.

•

Make sure the household breaker is shut off prior to working on any electrical lines.

•

The appliance, when installed, must be electrically grounded in accordance with local codes or, in the absence of
local codes, with the National Electrical Code, ANSI/NFPA 70, or the Canadian Electrical Code, CSA C22.1.

•

The electrical line must be a min. 14 gauge, and supply 120 Volts at 60 Hz (2 Amps).

Caution:Label all wires prior to disconnection when servicing controls. Wiring errors can cause improper anddangerous operation.

a© Travis Industriescb4090507d

100-01217_000

Installation (for qualified installers only)

17

Optional Wall Switch or Thermostat Installation
Do not connect 110-120 VAC to the gas control valve or wiring system of this fireplace. The switch andwiring must be installed by a qualified installer.
This fireplace includes an optional wall switch (with wire)to operate the fireplace burner without accessing theinternal on/off switch. A thermostat may be used instead.

OPTIONAL WALL SWITCH(included with fireplace)

Route the wire from inside the fireplace, through thegrommet on either side of the fireplace near the gas inlet(see at right) to the switch. The wall switch (or thermostat)
may bypass the fireplace on/off switch or be installed inPlace "WARNING"
label on switch cover.
parallel or series configuration (see below).
Caution:Label all wires prior to disconnection whenservicing controls. Wiring errors can cause
improper and dangerous operation.

Note:

When using a GreenSmart™ remote, use thereceiver for on/off operation (do not use a wall
switch or thermostat).
Make sure all wiring is secure and does notcontact hot or moving components.

Warning:

Parallel Connection
Thermostat / External
Switch ON
Thermostat / External
Switch OFF

Series Connection

On / Off Switch
ON
Heater is ON

On / Off Switch
OFF
Heater is ON

Heater is ON

Heater is OFF

To wire the heater in parallel, follow the directions below:aThermostat /External Switch ON
Thermostat /External Switch OFF

On / Off Switch
ON
Heater is ON

On / Off Switch
OFF
Heater is OFF

Heater is OFF

Heater is OFF

To wire the heater in series, follow the directions below:ab

On / Off Switchb

On / Off Switch

Thermostat(or External Switch) Wires

Thermostat(or External Switch) Wirescc© Travis Industries

4090507100-01217_000

18Installation (for qualified installers only)

Vent Requirements•

The gas appliance and vent system must be vented directly to the outside of the building, and never be
attached to a chimney serving a separate solid fuel or gas-burning appliance. Each direct vent gas appliancemust use its own separate vent system.

•

In addition to the requirements listed here, follow the requirements provided with the vent.

•

A firestop is required whenever the vent penetrates a wall, floor, or ceiling (passes through framing
members). Horizontal vent less than 48" (1219mm) above the fireplace must use the Travis Firestop (sku
93006094 - it incorporates a 3" (76mm) clearance above, 1" (25mm) clearance below and to the sides of thevent). Other penetrations only require a 1" (25mm) clearance and may use a standard firestop (make sure
the required 1" (25mm) clearance is met).

Vent Clearances•

The vent must maintain the required clearance to combustible materials to prevent a fire. Do not fill air
spaces with insulation.
Before 48" (1219mm) Rise
After 48" (1219mm) RiseSides
1" (25mm)
1" (25mm)
Above
3" (76mm)
1" (25mm)
Below Horizontal or 45° Section1" (25mm)
1" (25mm)
Vertical Termination
Horizontal

Required Firestop

Termination

Use a roof flashing and storm collar
whenever passing through the roof

Min. 3" (76mm)(1" or 25mm if a

Use a firestop wheneverpassing through a ceiling
Use a support box
on exposed ventminimum 48"or
1219mm above thefireplace)

Min. 1"(25mm)
Min. 1" (25mm)

Min. 1" (25mm)

Altitude Considerations•

This heater has been tested at altitudes ranging from sea level to 6,000 feet (1800 M). In this testing we have found thatthe heater, with its standard orifice, burns correctly with just an air shutter adjustment.

•

Failure to adjust the air shutter properly may lead to improper combustion which can create a safety hazard. Consult yourdealer or installer if you suspect an improperly adjusted air shutter.

© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

19

Approved Vent•

Side vent configurations use 8" (203mm) diameter Simpson Dura-Vent Model Direct-Vent Pro (or GS)*.

•Top vent configurations use 8" (203mm) or 6-5/8" (168mm) diameter Simpson Dura-Vent Direct-Vent Pro (orGS)*. If using 6-5/8" (168mm) diameter vent, attach the 8" (203mm) to 6-5/8" (168mm) reducer (Travis part #98900165) to the fireplace.
NOTE: When using 6-5/8” (168mm) diameter vent, make sure to accommodate the 3” (76mm) clearance
above the vent for the first 48” (1219mm) of rise (see vent clearances on page 18). Standard firestops do notinclude this clearance.
* Other vent may be approved with this fireplace. Check with the vent manufacturer for details.

•

Always use the high-wind cap (or high-wind sconce cap, part # 58DVA-HSCH or 46DVA-HSCH).

•

Installation instructions for Simpson Dura-Vent may be found at www.duravent.com

6-5/8" (168mm) Diameter Vent
Reducer - # 98900165

Vent Installation•

Slide the vent sections together and turn 1/4 turn until the sections lock inplace.

•

Screws are not required to secure the vent. However, three screws may be
used to secure vent sections together if desired.

•High temperature sealant is recommended at the appliance starter section
connection (use high-temperature silicone or Mill-Pac®).

•If disassembly is required, at time of re-assembly check to see if the ventcreates a tight fit. If it does not, apply high temperature sealant to the jointsof the affected sections.

•

Horizontal sections require a 1/4" (6mm) rise every 12" (305mm) of travel•

Horizontal sections require non-combustible support every three feet (e.g.: plumbing tape)© Travis Industries

4090507100-01217_000

20Installation (for qualified installers only)

Approved Vent Configurations
Restrictor Position•

Intake and exhaust restrictors are built into the appliance to adjust the flow rate of intake air and exhaustgases. Depending upon the vent configuration, you may be required to adjust the restrictor positions. The
charts for acceptable vent configurations detail the correct vent restrictor positions.

Exhaust Restrictor Adjustment
If the diffuser is required to be in position # 2, you may wish to adjust the diffuser while the exhaust
restrictor is removed.

FireboLeft Wx Roo

fall of F

ireboxLoosen these two screws
on the exhaust restrictor.

Slide the restrictor to the correct
restrictor position (see the illustration
below). The screw location indicates
restrictor position. In this example, therestrictor is set in position # 3. Tighten
the screws to secure the restrictor.
(closed) #6
#5
#4
#3
#2
(open - stock position) # 1
Left (vent) Side of Firebox© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

21

Intake Restrictor Adjustment
The intake restrictor is shipped in position # 1 (open). To adjust the restrictor to position # 2 (closed), follow thedirections below.

Restrictor Plate

Remove this screw.

Rotate the restrictor plate so
the left side hole lines up withthe screw-hole. Re-attach thescrew to lock the restrictor platein position # 2.

© Travis Industries

4090507100-01217_000

22Installation (for qualified installers only)

Diffuser Plate Adjustment
Certain vent configurations require the diffuser plate to be adjusted (refer to the approved vent configuration
charts for details). See the directions below to change the diffuser to position.
FireboBack W

all of Fx Roo

ireboxf

Remove the exhaust
restrictor.

1/4" Nutdriver

1/4" Nutdriver

Remove the diffuser.
DIFFUSER SIDE VIEW
Before (Stock - Position # 2)
Bend the round portion of the
diffuser 90° (position # 1).

After (Position # 1)

Secure the diffuser platewith the screws
removed earlier.

Replace the exhaust
restrictor (see “Exhaust
Restrictor Adjustment”
for restrictor settings).

© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

23

Side Vent Configuration with Horizontal Termination (no vertical rise)•

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor and diffuser
positions.

HINT: Travis Industries provides a minmum vent kit (sku 98900168). It includes a 4” (102mm) section and ahorizontal termination cap.
See the charts below todetermine maximum ventTermination

Optional 45° Elbow

Vent with No 45° Elbow
3 feet (0.915m)• Exhaust Restrictor # 1 (stock)• Intake Restrictor # 1 (stock)• Diffuser Position # 1
4' max 1.22m)

0 feet0 feet• Min. 4" (102mm) Horizontal Section• Max.48" (1219mm) Horizontal
Section(s)Vent with 1 45° Elbow• Exhaust Restrictor # 1 (stock)

3 feet (0.915m)• Intake Restrictor # 1 (stock)• Diffuser Position # 1© Travis Industries

2' max (0.61m))

0 feet0 feet4090507• Min. 4" (102mm) Horizontal Section• Max. 24" (610mm) Horizontal
Section(s)100-01217_000

24Installation (for qualified installers only)

Side Vent Configuration with Horizontal Termination (with vertical rise)•

Only one horizontal elbow may be used.
10 feet (3m)

20' max (6m)

Up to four elbows (45° or 90°) may be used.

15 feet (4.5m)•

5 feet (1.5m)

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor and diffuser
positions.

0 feet•22' max (6.7m)

22' max (6.7m)
Exhaust Restrictor # 4
Intake Restrictor # 2

20 feet (6m)

20 feet (6m)

Diffuser Position # 2 (stock)
Exhaust Restrictor # 4
Intake Restrictor # 1
Diffuser Position # 1

15 feet (4.5m)

15 feet (4.5m)

Exhaust Restrictor # 2 (stock)
Intake Restrictor # 1 (stock)
Diffuser Position # 1

10 feet (3m)

10 feet (3m)

5 feet (1.5m)

5 feet (1.5m)

0 feet
20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet(1.5m)

0 feet0 feetH2This is considered a horizontal

Horizontal length is calculated by adding

elbow (it does not matter

both lengths of horizontal run

whether it turns right or left).

(Horizontal Length = H1 + H2).

It may be a 90° or 45° elbow.
H1

This is considered avertical elbow© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

25•

Only one horizontal
elbow may be used.

20' max (6m)

Up to four elbows (45°or 90°) may be used.

15 feet (4.5m)•

10 feet (3m)

The termination must fallwithin the shaded area
shown in the chart. Use
the indicated restrictor
and diffuser positions.

5 feet (1.5m)•

0 feetSide Vent Configuration with Vertical Termination

40' max (12m)

40' max (12m)

35 feet (10.5m)

35 feet (10.5m)

30 feet (9m)

30 feet (9m)Exhaust Restrictor # 4
Intake Restrictor # 2

25 feet (7.5m)

25 feet (7.5m)

Diffuser Position # 1

20 feet (6m)

20 feet (6m)

Exhaust Restrictor # 2

15 feet (4.5m)

15 feet (4.5m)

Intake Restrictor # 1
Diffuser Position # 1

10 feet (3m)

10 feet (3m)

5 feet (1.5m)

5 feet (1.5m)

0 feet
20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feetH2This is considered a horizontal

Horizontal length is calculated by adding

elbow (it does not matter

both lengths of horizontal run

whether it turns right or left).

(Horizontal Length = H1 + H2).

It may be a 90° or 45° elbow.
H1

This is considered avertical elbow© Travis Industries

4090507100-01217_000

26Installation (for qualified installers only)

Top Vent Configuration with Horizontal Termination

Up to four elbows (45° or 90°) may be used.

•

May use 8" (203mm) or 6-5/8" (168mm) diameter vent (see page for 18 details).

•

Only one horizontal elbow may be used.

20 feet (6m)

10 feet (3m)0 feet21' max (6.4m)

20' max (6m)•

15 feet (4.5m)

The termination must fall within the shaded area shown in the chart. Use the indicated restrictor and diffuser
positions.

5 feet (1.5m)•

Exhaust Restrictor # 4

21' max (6.4m)

Intake Restrictor # 2

20 feet (6m)

Diffuser Position # 2 (stock)
Exhaust Restrictor # 4
Intake Restrictor # 1 (stock)
Diffuser Position # 2 (stock)

15 feet (4.5m)

15 feet (4.5m)

Exhaust Restrictor # 2
Intake Restrictor # 1 (stock)
Diffuser Position # 2 (stock)

10 feet (3m)

10 feet (3m)

5 feet (1.5m)

5 feet (1.5m)

0 feet

20' max (6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feetH2This is considered a horizontal

Horizontal length is calculated by adding

elbow (it does not matter

both lengths of horizontal run

whether it turns right or left).

(Horizontal Length = H1 + H2).

It may be a 90° or 45° elbow.
H1

This is considered avertical elbow© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)27•

Up to four elbows (45°or 90°) may be used.

•

Only one horizontal
elbow may be used.

•

May use 8" (203mm) or
6-5/8" (168mm)
diameter vent (seepage for 18 details).

20' max (6m)

15 feet (4.5m)

10 feet (3m)

The termination must
fall within the shaded
area shown in the chart.
Use the indicatedrestrictor and diffuser
positions.

0 feet•5 feet (1.5m)

Top Vent Configuration with Vertical Termination

40' max (12m)

40' max (12m)

35 feet (10.5m)

35 feet (10.5m)

Exhaust Restrictor # 4

30 feet (9m)

30 feet (9m)

Intake Restrictor # 2
Diffuser Position # 2 (stock)

25 feet (7.5m)

25 feet (7.5m)

20 feet (6m)

20 feet (6m)

15 feet (4.5m)

15 feet (4.5m)
Exhaust Restrictor # 3
Intake Restrictor # 2
Diffuser Position # 2 (stock)

10 feet (3m)

10 feet (3m)

5 feet (1.5m)

5 feet (1.5m)

0 feet

20' max 6m)

15 feet (4.5m)

10 feet (3m)

5 feet (1.5m)

0 feet0 feetH2This is considered a horizontal

Horizontal length is calculated by adding

elbow (it does not matter

both lengths of horizontal run

whether it turns right or left).

(Horizontal Length = H1 + H2).

It may be a 90° or 45° elbow.
H1

This is considered avertical elbow© Travis Industries

4090507100-01217_000

28

Installation (for qualified installers only)

Termination Requirements!

Venting terminals shall not be recessed into a wall or siding.

A

Minimum 9" (229mm) clearance from any door or window

B

Minimum 12" (305mm) above any grade, veranda, porch, deck or balcony

C

Minimum 3-3/8" (86mm) from outside corner walls
NOTE: Clearance in accordance with local installation codes and the requirementsof the gas supplier.

Roof
SurfaceRoof
Eaves

11" Min.
(279mm)6" Min.
(152mm)D

Minimum 12" (305mm) from inside corner walls
NOTE: Clearance in accordance with local installation codes and the requirementsof the gas supplier.

E

Minimum 11" (279mm) clearance below unventilated soffits or roof surfaces
Minimum 18" (457mm) clearance below ventilated soffits
Minimum 6" (152mm) clearance below roof eaves
NOTE: Vinyl surfaces require 24" (610mm)
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.

F

Minimum 12" (305mm) clearance below a veranda, porch, deck or balcony
NOTE: Permitted only if veranda, porch, deck, or balcony is fully open on a minumum of two sides beneath the floor.
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.

G

Minimum 48" (1219mm) clearance from any adjacent building

H

Minimum 84" (2134mm) clearance above any grade when adjacent to public walkways or driveways
NOTE: may not be used over a walkway or driveway shared by an adjacent building

I

Minimum 9" (229mm) clearance to any nonmechanical air supply inlet to the building or the combustion air inlet to any
other appliance.

J

Minimum 36" (914mm) clearance above any mechanical air supply inlet if within 10’ (3M) horizontallyK

Minimum 36" (914mm) from the area above the meter/regulator (vent outlet) - this extends 15’ (4.5M) above the regulator
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.

L

Minimum 36" (914mm) from the meter/regulator (vent outlet)
NOTE: Clearance in accordance with local installation codes and the requirements of the gas supplier.

M

Minimum 12” (305mm) above the roof line (for vertical terminations)

N

Minimum 24” (610mm) horizontal clearance to any surface (such as an exterior wall) – for vertical terminations
E
N
M

E
E

A

K
G

J

A
F

H

D

I

C
L
B

NOTE: Measure clearances to the nearest edge of the exhaust hood.

•

Use the vinyl siding standoff when installing on an exterior with vinyl siding.

•

Vent termination must not be located where it will become plugged by snow or other material© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

29

Hearth Requirements

Do not build a hearth morethan 1”(25mm) above theFloor Mounted

baseplate (this area mustremain clear for the access

Fireplaces

door).

If installed near carpet or othercombustible flooring, the fireplacemust be raised so the base of theunit is above the carpet surface or
flooring material.

WARNING:
A non-combustible hearth is not required. However, if
the heater is installed next to the floor, we recommenda hearth to protect the flooring surface fromdiscoloration or other negative impact from the heater.

RaisedA hearth is not required

Fireplaces

when the fireplace israised above the flooring
surface.

Fireplace Stand© Travis Industries

4090507100-01217_000

30

Installation (for qualified installers only)

Facing Requirements•

This appliance is designed to allow for drywall (or other combustible facing) to contact the sides and top of
the front of the fireplace.

•

Tile or other non-combustible facing may be placed on the front of the fireplace (see "Facing Overview" onpage 31 for further details).

Drywall Installation

Drywall Installation Drywall may beinstalled up to the front edge of the fireplace.
If the fireplace is raised, drywall up to thebottom edge as well.

all

yw

Dr

Do not install drywall (or any
other combustible) in frontof the fireplace.

TOP VIEW
Framing

Fireplace

Nailing Bracket
Drywall© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

31

Facing Overview
Upgrade faces are available for this fireplace and may influence facing installation. Consult with yourTravis Dealer if you are using an upgrade face.
Optional non-combustible facing may be installed on the fireplace. Use the guidelines below to determine thelocation (also see the following pages for detailed diagrams.
Any non-combustible facing under 1" (25mm) thick (see "Thin Facing" on page 32).

Masonry LineAny non-combustible over 1" (25mm) thick (see "Thick Facing" on page 34).

Hearth Line

Non-combustible hearth/facing should be installed up to this location (1" (25mm) above the base of thefireplace). The fireplace may be raised to accommodate thicker hearth materials.
Tile Line
Masonry Line

Tile Line

ry

n
so
Ma
e
in
eL

e

Lin

Masonry Line
Tile Line

Til

SPECIAL INSTRUCTIONS FORWILMINGTON FACES
Remove the center deflector (use needlenose pliers if necessary).

e
Lin neryion ile L
s
T
Ma

rth

Tile Line
Masonry Line

a
He

rth

e

Lin

Masonry Line
Tile Line

a
He

e

Lin

These tabs bend down
to allow for removal.

Re-attach the deflector to the louver.
Bend the tabs as shown, making surethe deflector is secure and flat.
WARNING: The deflector must be
replaced in its original position if a
different face or grill is used.

NOTE: The hearth or facing can extend nogreater than 1” (25mm) above the base of thefireplace. The fireplace may be raised toaccommodate thicker hearth materials.

Optional Faceplates – Sizing ChartName
FPX Artisan, Classic, Fr Ctry
Winthrop Victorian Lace
Wilmington Hearthview
Winthrop Bungalow© Travis Industries

Height35-3/4”(908mm)34-1/8”(867mm)35-3/4”(908mm)
34”(864mm)Width
41”(1041mm)36-7/8”(937mm)41”(1041mm)36-7/8”(937mm)Notes
45-3/4” (1162mm) Radius – May fit over top of tile
facingOptional facing will butte to edge of faceplate (tileline)
May fit over top of tile facing
Optional facing will butte to edge of faceplate (tileline)

4090507100-01217_000

32Installation (for qualified installers only)Thin Facing Installation (tile, marble, or other non-combustible under 1" (25mm) thick)

Tile Line

Upgrade faces are available for this fireplace and may influence facing installation. Consult with yourTravis Dealer if you are using an upgrade face.

ine

eL

Til

Facing is installed to thisedge of the fireplace.

all

yw

Dr

ine

hL

Do not install tile (or other material)in front of the glass frame,
convection channel, or access panel
openings. This area must remain
open to access internal components
and for convection air.

rteaTile LineH

Floor-Mounted Fireplaces or Raised Hearths:
Build the hearth 1" (25mm) maximum above thebase of the fireplace. The fireplace may be raised toaccommodate thicker hearth materials.

TOP VIEW
Framing
Nailing Bracket

Fireplace

Raised Fireplaces:
Facing is installed 1" (25mm)
maximum above the base of thefireplace.

Drywall

FRONT VIEW
1-1/8"
29mm

Tile

NOTE FOR FPX FACES:FPX arched faces require the FPX Face
Upgrade Kit (sku 98500686) and atriangular piece of facing in these upper
corners. See the instructions included
with the face for further details.

34-1/4"870mm

7-7/8" (200mm)

1" (25mm)

2-7/8"(73mm)© Travis Industries

37"
940mm

40905072" (51mm)

100-01217_000

Installation (for qualified installers only)

33

Thin Facing Installation (tile, marble, under 1" (25mm) thick) - Side View
Drywall

Raised Fireplace
Tile or other facing under 1'' (25mm)(with no Hearth)

thick.

Face

SIDE OFFIREPLACE

Note how the facing extends 1'' (25mm)
above the base of the fireplace.

1'' (25mm)
Fireplace Support
Floor

Floor-Mounted Fireplace

Drywall(with Hearth)

Tile or other facing under 1''(25mm) thick.

Face

SIDE OFFIREPLACEHearth: note how it extends under the face max. 1'' (25mm) thick. The fireplace may beraised to accommodate thicker hearthmaterials.
Max. 1'' (25mm)
Floor© Travis Industries

4090507100-01217_000

34Installation (for qualified installers only)

Thick Facing Installation (stone, brick, or other non-combustible over 1" (25mm) thick)Masonry LineIf using a Fireplace Xtrordinair (FPX) arched face, see "Thick Facing with a Fireplace Xtrordinair Arched
Faces" on page 35.

ry

on

s
Ma

e

Lin

all

yw

Dr

Do not install masonry (or othermaterial) in front of thefireplace. This area must remain
open to install the face.

rth

e

Lin

Masonry LineaHe

Floor-Mounted Fireplaces or Raised Hearths:
Build the hearth 1" (25mm) maximum above thebase of the fireplace. The fireplace may beraised to accommodate thicker hearth materials.

TOP VIEW - Protruding Masonry
Framing
Fireplace

Nailing Bracket
Drywall

Raised Fireplaces:
Masonry is installed 1" (25mm)
maximum above the base of thefireplace.

FRONT VIEW

Masonry

TOP VIEW - Recessed Masonry
Framing

Fireplace35-3/4"908mm

Drywall(or cement board, etc.)

Masonry
1"

NOTE: The nailing brackets are not used for this typeof installation - secure the fireplace to the floor withthe brackets along the base of the fireplace.

© Travis Industries

41"
1041mm4090507100-01217_000

Installation (for qualified installers only)

35

Thick Facing with Fireplace Xtrordinair (FPX) Arched Faces
The following illustration shows facing considerations for those fireplaces utilizing FPX arched faces.
The facing must be non-combustible and over 1" (25mm) in depth.
Masonry LineThe Fireplace Xtrordinair 864
Masonry Template isrecommended for masonry
installation (sku 98500688). The
template helps locate andsupport the masonry as it being
installed.

all

yw

Dr

ine

hL

rt
ea

H

Before installing masonry, install
the FPX Face Upgrade Kit(98500686). This covers theupper corners.

Floor-Mounted Fireplaces or Raised Hearths:
Build the hearth 1" (25mm) maximum above thebase of the fireplace. The fireplace may beraised to accommodate thicker hearth materials.
Raised Fireplaces:
Masonry is installed 1" (25mm) maximum
above the base of the fireplace.

FRONT VIEW

5"
127mm

TOP VIEW
Framing

Fireplace45-1/2" (1156mm) Radius

Nailing Bracket

35-3/4"908mm

Drywall

Face

Masonry1"
41"1041mm© Travis Industries

4090507100-01217_000

36

Installation (for qualified installers only)

Thick Facing Installation - Side View
DrywallFloor-Mounted Fireplace(with Hearth)

Masonry or other non-combustible
over 1'' (25mm) thick

SIDE OFFIREPLACE

Face
Hearth (note how it extends under the face - max. 1''(25mm) thick). The fireplace may be raised toaccommodate thicker hearth materials.

Max. 1'' (25mm)
Floor

Drywall

Raised Fireplace(with no Hearth)
Masonry or other non-combustible
over 1'' (25mm) thick.

SIDE OFFIREPLACE

Face (Behind Masonry)
The masonry extends 1'' (25mm)
above the base of the fireplace.

1'' (25mm)
Fireplace Support
Floor© Travis Industries

4090507100-01217_000

Installation (for qualified installers only)

37

Mantel Requirements
Combustible Mantels•

Use the table below to determine the maximum mantel depth allowed. The mantel depth (measured from theface of the fireplace) must fall in the shaded portion of the table.

•

Any material that protrudes more than 3/4” (19mm) from the non-combustible facing is considered a mantel
and must meet the mantel requirements.

Combustible Mantel(457mm) 18+"(432mm) 17"(406mm) 16"(381mm) 15"(356mm) 14"

MantelHeightAbove
Face (a)

0”
1"
(25
2" mm
)
(5
3" 1mm(76 )m
4"(10 m)
2m
5"(12 m)
7
6"(15 mm)
7" 2mm(1)
8" 78m(2
m)
9" 03mm(2)
10 29m" (2 m)
54m
11m"
12 (279 )" (3 mm
05 )mm)

Maximum Mantel Depth (b)(330mm) 13"(305mm) 12"(279mm) 11"(254mm) 10"(229mm) 9"(203mm) 8"(178mm) 7"(152mm) 6"(127mm) 5"(102mm) 4"(76mm) 3"(51mm) 2"(25mm) 1"0”ba36-3/4"
Combustible mantel columns (legs) that protrude

933mm

more than 3/4" (0.75mm) from the glass frame
must meet the sidewall clearance. If they
protrude 3/4" (0.75mm) or less, they must meetthe facing clearance 2-1/4" (57mm) from theglass frame.
Base of the Fireplace

Non-combustible mantel columns do not have aminimum clearance.

Examples:- If you wish to have an 8” (203mm) deep mantel, it must be at least 6-3/4” (171mm) above the fireplace face (44-3/4”, 1137mm above the base).
- If you wish to have a mantel 8” (203mm) above the fireplace face, it must be no deeper than 9” (229mm).

Non-Combustible Mantels
Non-combustible mantels must meet the clearances listed for combustible mantels. However, if you do wish to
reduce the clearances by using a non-combustible mantel, the following requirements must be met:••

Non-combustible mantel
and facing must extend
from the top of theappliance to the top
surface of the mantel.
A non-combustible
header must be used(metal stud).

Drywall
Non-Combustible Framing (metal studs)
must be used for the header.

SIDE OF FIREPLACE

Non-Combustible Mantel
Non-Combustible Facing© Travis Industries

4090507100-01217_000

38

Finalizing the Installation (for qualified installers only)

Steps for Finalizing the Installation
1.
2.

3.

Remove the glass (see page 40).
NOTE:
If using propane (LP) convert the appliance prior to installing the logs.
We recommend you purge the gas line at this time (with the glass removed). This allows gas to be detectedonce it enters the firebox, ensuring gas does not build up.
NOTE:
If using firebacks, install them prior to adjusting the accent light deflectors.
Carefully bend the accent light deflectors outwards to 45* (see “a” below). Take care to prevent damage to thebulbs. Make sure the two accent light bulbs are in place. The assembly may be removed for bulb replacement(see “b” below).
NOTE: .Take care to not touch the bulb with your fingers (use a cloth or paper towel).

a

b

4.

Install the four AA batteries (included in the owner’s pack) into battery holder (see the illustration below). The AA
batteries act as a power backup in case the household (AC) power goes out. Install the 9v battery (included in
the owner’s pack) into control panel light assembly (see the illustration below). The battery holder is held in placewith Velcro and may be removed for easier access.

Battery Holder for
Control Panel Lights
9
Ba v
tte
ry

AA

Lift up and swing the lower
grill down to acces the area
below the firebox.

Swing the concealment
cover up and slide it back to
expose the controls.

AA
Ba

AA

Ba

tte

tte

ry

ry

AA
Ba
tte
Ba
ry
tte
ry

AA
Battery
HolderAA Battery Tray

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)
5.
6.
7.
8.
9.

39

Install the logs (see page 42).
Replace the glass.
Start the heater.
Leak test all gas joints.
Check the air shutter following the directions below.

Air Shutter Adjustment
Let the heater burn for fifteen minutes (make sure the logs and glass are in place). The flames should beyellow with no sooting. Adjust the air shutter, if necessary, to achieve the correct looking flame.

Correct

Not Enough Air

Too Much Air

Flames should be blue at thebase, yellow-orange on the top.

If the flames are too tall or sooty on theends, open the air shutter.

If the flames are all blue andshort, close the air shutter.

Air Shutter Adjustment

Center Burner Air Shutter Control(GOLD)Left = Less Air

Outer Burner Air Shutter Control

Right = More Air(RED)
Left = Less Air

NOTE: you may wish to use pliers to adjust the front
air shutter. Typically, the front air shutter is fully closed(left) on NG, fully open (right) on LP

Right = More Air

10. Turn the flame adjust knob to its highest position - the flames should not contact the top of the firebox. Check the flameon low position. The flames should burn off of each burner hole. If the heater does not work correctly, contact your Travis
dealer for a remedy.
11. Give this manual to the home owner for future reference and fully explain operation of this heater. For comprehensive
operating and maintenance instructions, refer to the Owner's Manual (part # 100-01219).
ACID WASH WARNING: Before installing the faceplate, make sure any masonry that has been treated with acid wash has
been properly neutralized (this is used primarily with brick faces). Acid wash (muriatic acid) is used to remove excess mortar.
If not properly neutralized with an ammonia solution, the plated face may develop a permanent tarnish when the acidevaporates over time. Contact your dealer if uncertain your facing has been properly neutralized.

© Travis Industries

4090507100-01217_000

40Finalizing the Installation (for qualified installers only)

Glass Frame Removal and Installation
Warning:

The appliance must be completely cool before removing the glass.

Warning:

Do not strike or slam the glass.

Based upon the face being used, either:a (a) swing the access door down and remove the top grill,(b) remove the face (unscrew or lift off - see the instructions included with the face for details).
Open the six latches holding the glass frame in place (start with the bottom three) - follow thedirections shown to the right.

Top ofFirebox

Latch
Glass

b

Lift the glass frame up andpull it forward to remove.
NOTE:
You may need to lift
the glass frame
while re-attaching.

Catch(on glass frame)

Re-Attaching the Glass Frame:a) Hang the glass frame on the firebox.
b) While holding in place, attach the upper latches(follow the instructions above in reverse).
c) Lift the glass frame slightly and attach the lower latches.
NOTE: Make sure the glass frame is all the way in place - it should be flush withthe front of the fireplace when installed.

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)

41

Glass Frame Removal and Installation (continued)
The latch can come loose from glass frame anchor. This occurs when it is turned 1/4 turn when it isdisengaged. Follow the directions below to re-install the latch if it becomes loose.

Hold the latch at an angle and insert it into the slot on the glass frame anchor.

Latch

NOTE: this slot may be at adifferent angle than illustrated.
Top ofFireboxGlass Frame
Anchor

Note how the washer on the latch fits behind the flange on theglass frame anchor.

Once fully inserted, turn the latch until it is upright.

© Travis Industries

4090507100-01217_000

42Finalizing the Installation (for qualified installers only)

Log Set Installation
Logs in Place – FRONT SIDE (gas control valve side)
NOTE: This fireplace has a front side and back side. The front side (pictured belowj) is the side with thegas control valve.

Logs in Place – BACK SIDE

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)43

Bend these two tabs up 90°. They are used

Center Log Installationas pins to locate the center log.

The log shelf has two tabs
used to align the center log.
Bend these tabs as shown to
the right.

Place the center log in place.
Make sure the two tabs on thelog shelf insert into the twoholes on the bottom of the log.

Once in place,rotate the log
clockwise until
the indents in thelog contact thegrate.

© Travis Industries

4090507100-01217_000

44Finalizing the Installation (for qualified installers only)

Front Left Log
Place the front left log as shown below. There is a ledge on the bottom of the log that aligns with theedge of the center burner.

When in place, the front left log has a small gap to the center log.

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)

45

Front Left Upper Log

There are two pins on the front
left log. The pin to the right isused to locate the front left upperlog.

The front left upper log has a groove andone hole on the bottom. The groove fits
over the edge of the burner.

When in place, the front left upper log looks
like the picture to the right.

© Travis Industries

4090507100-01217_000

46

Finalizing the Installation (for qualified installers only)

Front Upper Center Log
The front upper center log has
two holes on its bottom
surface. One of the holes fits
over the pin on the center log(see picture to the right). The
other fits over the pin on thefront left log.

When in place,the front upper
center log looks
like the picture
to the right.

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)

47

Back Left Log

The back left log fits to the left of the centerlog.

The groove on the bottom of the log fits overthe upper burner tray.

Make sure to slide the log towards thecenter of the firebox. When in place, the log
will appear as shown in the picture to theright.

© Travis Industries

4090507100-01217_000

48

Finalizing the Installation (for qualified installers only)

Right Ember Chunk

The right ember chunk is installed from theback. The groove on the bottom of theember fits over the edge of the upper burnertray. It wedges between the two logs..

When in place, the left ember chunk looks
like the picture to the right.

Back Ember Chunk

The back ember in placed on theback right side as shown in the
picture to the right. Make sure it
is not over any burner holes.

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)

49

Back Left Log

The pin on the center log inserts into thehole on the back of the back left log.

This groove on the log fits over the grate.

When in place, the log looks like the picture
to the right.

© Travis Industries

4090507100-01217_000

50Finalizing the Installation (for qualified installers only)

Back Upper Right Log

Pins on the center log and back right log
help locate this log.

When in place, the back upper right log
looks like the picture to the right.

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)

51

Ember Placement
A bag of embers is provided to further enhance the firebox. Place the embers on the firebox floor and on
the outer burner (especially over exposed rivets on the burner). Do not place embers over any of theburner holes or air channels. See the picture below.

NOTE: When placing the embers, place one ember on both sides of the accent light deflectors (seeillustration below). This helps block light from exiting the slot on the deflector and creating a line of light.

© Travis Industries

4090507100-01217_000

52Finalizing the Installation (for qualified installers only)

LP Conversion Instructions
Install the conversion kit prior to installing the gas line to ensure proper gas use.
1

Remove the glass (see page 38). Remove the logs and embers (if installed - page 42).

2

Remove the grate , firebacks, and center burner (see illustration below).

1/4" Nutdriver

Remove the grate from both sides.
NOTE: lift the burner to remove the grate.

Remove the log shelf

Four screws hold the center
burner in place. Slide theburner to the right and up to
remove.

© Travis Industries

4090507100-01217_000

Finalizing the Installation (for qualified installers only)
3

53

Follow the directions below to remove the outer burner and replace the orifices.
aRemove theouter burner.

Make sure this gasket isreplaced when re-installing.

Center Burner Orifice
Outer Burner OrificebcRemove this mixing tube cover.

Use a 1/2” open end wrench to unscrew the two orifices.
d

Manifold

1/2" WrenchCenter Burner Orifice

Apply thread sealant to
the LP orifices prior to
installation. Use thechart below to identify
the correct orifices.

Outer Burner OrificeeScrew each LP orifice inso the orifice protrudes
15/16” (23.8mm)
indicating full insertion.

© Travis Industries

15/16”
23.8mmLook here for the orifice
identification
NG
Center #48
Outer #44

4090507LP#55#55
100-01217_000

54Finalizing the Installation (for qualified installers only)

4aRemove the pilot orifice following the instructions below. Replace with the propane pilot orifice
Lift the pilot hoodcoff the pilot

Remove the orifice and replace with the LP orifice. Screw theorifice all the way in and replace the pilot hood.

assembly.
Orifice Identification:
LP (Propane) Orificeb

35

Use a hex wrench to35

unscrew the orifice.

NG (Natural Gas) Orifice62
5/32" Hex

NOTE: when re-attaching,
this pin lines up with thenotch in the pilot hood.

5

Replace the firebox components. Install the logs and embers. Replace the glass.

6

Remove and discard the screws (see “a” below) holding the stock regulator in place (see “b” below).
Remove the stock regulator and gasket (see “c” below). Place the LP regulator in place, making
sure the pre-fitted gasket (see”c” below) is in place. NOTE: There is a label on the base of theregulator knob indicating regulator type (NG or LP). Secure the regulator with the screws included
with the regulator – tighten to 25 lb-in of torque (2.82 NM). Place the included label on the valve bodywhere it can be easily seen to insure proper identification. NOTE: Leak test this area after theheater is installed, gas is connected, and the main burner is lit.

aT-20 Torx or
Slotted Screwdriver

b

c

d

7

Make the gas line connection, bleed the gas line (if applicable), start the heater and thoroughly leaktest all gas connections and the gas control valve.

© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)

55

Fireback Installation
WARNING:
service.

Turn off gas to the appliance and make sure it has fully cooled prior to conducting

1

Remove the glass frame and logs.

2

Remove the front and rear grates (NOTE: lift the burner slightly to remove the grate - see theillustration below).
NOTE: If the accent light deflectors have been bent, carefully bend the accent light deflectors
inwards on both sides (NOTE: do not over-bend these deflectors, they will break off if over-bent).

3

Remove and discard the steel ember trays.

© Travis Industries

4090507100-01217_000

56

Optional Equipment (for qualified installers only)

4

Carefully place the floor
firebacks into position.
You must tip them under
and around the corners of
the burner. Once inplace, bend the accent
light deflectors back to
the correct position (takecare to not damage thehalogen bulbs).

5

Carefully replace the front
and rear grates (they reston top of the floor
firebacks).

6

Install the side firebacks
following the directions
below.

aRemove the clips on both sides (loosen the screws
a couple turns and slide clips up and out).
5/16" Nutdriver

7

Restore the fireplace tothe correct configuration.
b Place the side firebacks into position.

cSecure the clips to anchor
the side firebacks.

The ceramic firebacks are fragile. Ensure proper alignment of individual pieces in each step. To achieve
the ideal appearance, you may need to make slight adjustments.

© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)

57

Grill Installation
Certain faces allow for installation of an upper and lower grill. Follow the directions below to install.

Upper Grill
Installation

Hold the grill at an angle and insert the lower
slot over the bushing on the fireplace (bothsides). You may need press on the grill to get
the tab over the bushing (this prevents thegrill from accidentally falling off).

Swing the grill upwards to engage the upper
slot. You will need to lift the grill slightly to
get it over the bushing. Once in place thegrill is held in place by gravity.

Lower Grill Installation

Hold the grill at an angle and insert the lower
slot over the bushing on the fireplace (bothsides). You may need press on the grill to get
the tab over the bushing (this prevents thegrill from accidentally falling off).

© Travis Industries

Bend this the tab over onboth sides. This is theend-stop for the lower grill,it allows the grill to swing
forward.

4090507

Swing the grill upwards to engage
the upper slot. You will need to lift
the grill slightly to get it over thebushing. Once in place the grill isheld in place by gravity.

100-01217_000

58

Optional Equipment (for qualified installers only)

Extra Room Power Heat DuctSKU 98500769

Special Instructions for 864 ST
The 864 ST has a removable cover plate shield below the heat duct connections. This allows more heatto be routed to the power heat ducts (see below for details). Otherwise the heat duct is installed thesame as an 864TRV (one heat duct kit maximum, manually-controlled on/off operation – see wiring
diagram below).

Power Heat Duct Wiring Diagram
RheostatJunction Box

Power Supply

Power Heat Duct Wiring Diagram• 864 TRV
• 864 ST• 864 HH (sn 3407-001009 or less)Hot(black)Hot(black)Common(white)Common(white)Ground(green)Ground(green)BlowerAssembly-Remove the Heat Shield Cover Plate
Remove and discard the power heat
duct cover plate.

Remove and discard the circular coverplate attached to the heat shield.

NOTE: an additional power heat
duct hook-up location is provided
on the right side (it is along the topedge of the fireplace).
NOTE: Only one hook-up may be
used (do not hook up two heatducts to the fireplace).

© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)

59

Andiron Installation
Install the andirons after installing all other optional equipment (firebacks, accent light, etc) but before
installing the logs.
Part Numbers: Arabesque 98500633 -- Colonial 98500631 -- Wrought Iron 98500632

b

a Disassemble one of the andiron

Lift up on thebrackets.

burner and slide
the upper portionof the bracket into
the gap between
the burner andgrate.

cd5/32” Hex
Wrenche

Pull on thebracket so it
is all the way
forward.

Attach the andiron to thelower portion of thebracket with the included
screw (use the included
5/32” hex wrench).

Attach the andiron (withbracket) to the bracket on
the fireplace using thescrews removed in step “a”.
You may need to bend thebracket slightly to allow the
andirons to stand vertically.

f© Travis Industries

4090507

Repeat steps “a” through “e”
for the opposite side.

100-01217_000

60

Optional Equipment (for qualified installers only)

GreenSmart™ Remote Control Installation
Packing List
•
•
•
•
•
•
•
•
•
•
•
•
•
•

Transmitter
Receiver (with Cover Plate & Switch)
Fan Control Module
VelcroLP or NG Stepper Motor (with screws and label - attaches to Valve)
Wire Harness(2) Power Leads(4) AA Batteries (inside receiver box)
(2) #8 x ½” Machine Screws(2) Wire Ties
Torx T-20 Wrench
Wall Mount (for placing the transmitter on a wall)(2) Drywall anchors (for wall mount)(2) #8 x 3/8” Type B Screws© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)

61

Overview
The GreenSmart remote installs onto a 864 fireplace and replaces the stock wiring harness. Before
installing, familiarize yourself with the stock and updated wiring diagrams (see the illustrations on thispage and and following page).
Stock Wiring Diagram

Spark RodAccentLight (s)Pilot
SensorAccent Light
Rheostat
Pilot Ground
Optional
BlowerHookup

CN4

Comfort Control
Valve

PILOT
SENSOR

120 VACPower In

DIGITALFIREPLACE

CN0

BURNERAC
ADAPTERCONTROLSPARK ROD

VALVE

CN2

COMMAND

POWER

CN1

GROUND

POWER SUPPLY

IPI / CPI
Blue

Red
Black

Red

Red

Red

ON / OFF

Black

Blue

Green

Red

OrangeYellow / Green

VALVE

CN3

DIAGNOSTIC

Green
White

Black

Blue

White

CONTINUOUS
PILOT

COMFORT
CONTROLGREENSMART
PILOT© Travis Industries

4090507

AA
BATTERY
TRAY

MAIN BURNER

100-01217_000

62

Optional Equipment (for qualified installers only)

GreenSmart Wiring Diagram
CN4

Comfort Control
Valve

Spark Rod

Pilot
SensorPILOTSENSOR

DIGITALFIREPLACE

CN0

BURNERSPARK ROD

Pilot
GroundCONTROLVALVEDIAGNOSTICCOMMANDGROUND

CN3

STEPPER MOTOR

POWER

CN1

CN2

BURNER CONTROLVALVERECEIVER
OrangeGreen

Yellow / Green

RemoteReceiver
IPI / CPI

Blue

TOP

White

CONTINUOUS
PILOT(4) AA Batteries

FAN CONTROLFan Controller
POWER

INTERMITTENT
PILOT

110V OUTFAN

AUX OUT

120 VACPower InCOM

AccentLight (s)Thermodisk
Optional
Blower(s)Accent Light
Rheostat© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)

63

Installation
WARNING:

Make sure power to the fireplace has been shut off prior to installation.

NOTE:

Refer to the wiring diagram on page 62 while making wiring harness connections.

1

Remove the concealment cover from the front of the fireplace (see Figure 1).

Figure 1

2

Unscrew the four screws holding the control cover in place (see Figure 2). Carefully remove thecontrol cover (see Figure 3)

Figure 2

3

Figure 3

Unplug the ac adapter from the power harness (see Figure 4). You can leave the ac adapter
plugged into the wiring harness.

Figure 4© Travis Industries

4090507100-01217_000

64

Optional Equipment (for qualified installers only)
4

Disconnect the molex connector leading to the gas control valve (see Figure 5).
WARNING: The tabs on the gas control valve are fragile. Take care when removing the molex
connector to not pull or damage the wires or tabs.

Figure 55Disconnect the two leads on the back of the control panel for the IPI / CPI switch (continuous pilot/ greensmart pilot – see Figure 6).

Figure 66

Disconnect the comfort control valve connection (see Figure 7). Disconnect the burner control
connector from the fireplace burner control (see Figure 8).

Figure 7© Travis Industries

4090507

Figure 8100-01217_000

Optional Equipment (for qualified installers only)
7

Unscrew the on/off/battery plate from the control panel (see Figure 9). Pull the plate and wiringforward (see Figure 10).

Figure 98

Figure 10

The control panel has plastic wire-locks attached to the back (see Figure 11). Un-hook the wires
from the wire-locks and remove the wiring harness, plate, battery holder, and ac adapter (seeFigure 12). These items may be discarded.

Figure 11965

Figure 12

Use the included torx wrench to remove the stock regulator (see Figure 13). These items may bediscarded.

Figure 13© Travis Industries

4090507100-01217_000

66

Optional Equipment (for qualified installers only)
10

The stepper motor (adjustable regulator) has an installation sheet included with it – make sure tofollow all of the directions. Place the stepper motor on the gas control valve (see Figure 14) –MAKE SURE IT IS CORRECTLY ORIENTED. Secure using the screws included with the motor(see Figure 15) – tighten to 25 Lb-inches. Leak test this area after installation to verify proper
installation.

Figure 15

Figure 14

11

Place the GreenSmart wiring harness in front of the fireplace, noting the position of eachconnector (see .Figure 16).

Figure 16

12

Attach the wiring harness to the burner control (see Figure 17). Attach the gas control valve
molex connector (see Figure 18).

Figure 17© Travis Industries

Figure 184090507100-01217_000

Optional Equipment (for qualified installers only)
13

Attach the blue and white wires to the IPI/CPI switch (see Figure 19). Connect the wiring
harness to the stepper motor (see Figure 20).

Figure 19

14

67

Figure 20

Attach the wiring harness to the comfort control valve connection (see Figure 21).

Figure 21

15

Place the fan controller near the front of the fireplace to the left and connect it to the wiring
harness (see Figure 22). Attach the power cord from the fan controller to the AC connection (seeFigure 23). MAKE SURE TO TURN THE FAN CONTROLLER ON (“-“ SYMBOL).

Figure 23
Figure 22© Travis Industries

4090507100-01217_000

68

Optional Equipment (for qualified installers only)
16

Disconnect the power lead from accent light and connect it to the power lead included with this kit(see Figure 24). Attach the power lead to the fan controller in the “AUX OUT” receptacle (seeFigure 25).

Figure 24

Figure 25

NOTE: If using the optional fan, you will want to disconnect its power lead and connect it to
the extra power lead included with this kit, then connect it to the “FAN” receptacle on
the fan controller.
17

Attach the included velcro to the bottom of the fan control module and to the base of the fireplacenear back left of the fireplace. Slide the fan controller into place and secure using the velcro(see Figure 26).

Figure 26© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)
18

Pull the “RECEIVER” connector through the control panel and attach to the receiver (see Figure27). Then attach the receiver to the control panel with the two #8 machine screws (see Figure
28).

Figure 27

19

Figure 28

Place batteries into the receiver and transmitter (see Figure 29). Calibrate the receiver to thetransmitter (see Figure 30 - use a paperclip to press the “PRG” button, let it beep, then press any
button on the transmitter – the receiver should beep 5 times – see the operating instructions forfurther details).

Figure 29

20

69

Figure 30

Place the receiver coverplate (and switch) over the receiver (see Figure 31) and attach with thetwo screws included with the receiver (see Figure 32)© Travis Industries

4090507100-01217_000

70

Optional Equipment (for qualified installers only)
Figure 31

21

Clip any excess wiring into the wire clips on the back of the control panel (see Figure 33). Use
the included wire ties, if necessary, to keep all wiring from contacting any hot or moving
components. Re-attach the control panel (see Figure 34) and shroud (see Figure 1).

Figure 33

22

Figure 32

Figure 34

A wall mount is included with this kit for the remote. It may be mounted to the wall for easy
access and storage. Use the included drywall anchors (and screws) to secure it to the wall (seeFigure 35).

Figure 35

23

Restore power to the fireplace and test operation of the remote (see the instructions included withthe remote).

© Travis Industries

4090507100-01217_000

Optional Equipment (for qualified installers only)© Travis Industries

409050771

100-01217_000

72

Index

Index
Additional Items Required ............................................ 7
Andiron Installation ....................................................... 59
Air Shutter Adjustment ................................................. 39
Altitude Considerations ................................................ 18
Approved Vent Configurations ..................................... 20
Approved Vent ............................................................. 19
Battery Installation ........................................................ 38
Clearances ................................................................... 11
Converting the Fireplace to Side Vent Configuration.... 9
Diffuser Plate Adjustment ............................................. 22
Dimensions .................................................................. 6
Drywall Installation ....................................................... 30
Electrical Connection (required) ................................... 16
Exhaust Restrictor Adjustment ..................................... 20
Extra Room Power Heat Duct ...................................... 58
Facing Overview .......................................................... 31
Facing Requirements ................................................... 30
Features ....................................................................... 6
Fireback Installation ..................................................... 55
Fireplace Placement Requirements ............................. 11
Fuel .............................................................................. 14
Gas Inlet Pressure ....................................................... 14
Gas Line Connection .................................................... 14
Gas Line Location ........................................................ 14
Gas Line Requirements................................................ 14
Glass Frame Removal and Installation......................... 40
Grill Installation............................................................. 57
Hearth Requirements ................................................... 29
Heating Specifications .................................................. 6
Index ............................................................................ 72
Installation Options ....................................................... 6
Intake Restrictor Adjustment ........................................ 21
Listing Details ............................................................... 2
Log Set Installation ....................................................... 42
LP Conversion Instructions .......................................... 42
Mantel Requirements ................................................... 37© Travis Industries

Minimum Framing Dimensions – Top or Side Vent Configuration .12
Nailing Brackets ........................................................... 13
Overview ...................................................................... 2
Packing List .................................................................. 7
Raised Fireplaces ........................................................ 11
Side Vent Configuration with Horizontal Termination (no vertical rise) ..... 23
Side Vent Configuration with Horizontal Termination (with vertical rise).... 24
Side Vent Configuration with Vertical Termination ....... 25
Recommended Installation Procedure ......................... 7
GreenSmart™ Remote Control Installation .................. 60
Restrictor Position ........................................................ 20
Safety Precautions ....................................................... 4
Steps for Finalizing the Installation ............................... 38
Termination Requirements ........................................... 28
Thick Facing Installation with FPX Arched Faces ........ 35
Thick Facing Installation ............................................... 34
Thin Facing Installation ................................................ 32
Top Vent Configuration with Horizontal Termination .... 26
Top Vent Configuration with Vertical Termination ........ 27
Vent Clearances........................................................... 18
Vent Installation............................................................ 19
Vent Requirements ...................................................... 18
Optional Wall Switch or Thermostat Installation ........... 174090507100-01217_000