INSTALLER / CONSUMERSAFETY INFORMATION
PLEASE READ THIS MANUAL
BEFORE INSTALLING AND USINGAPPLIANCE.
WARNING!
IF THE INFORMATION IN THISMANUAL IS NOT FOLLOWED
EXACTLY, A FIRE OR EXPLOSION
MAY RESULT CAUSINGPROPERTY DAMAGE, PERSONALINJURY OR LOSS OF LIFE.

Stardance®
Direct Vent/Natural Vent
Gas Heater

FOR YOUR SAFETY
Installation and service must be
performed by a qualified installer, service
agency or the gas suppler.
WHAT TO DO IF YOU SMELL GAS:
•
•
•

•

Do not try to light any appliance.
Do not touch any electric switch; do
not use any phone in your building.
Immediately call your gas supplier fromyour neighbor’s phone. Follow the gas
supplier’s instructions.
If you cannot reach your gas supplier,call the fire department.

DO NOT STORE OR USEGASOLINE OR OTHER
FLAMMABLE VAPORS AND
LIQUIDS IN THE VICINITY OF THISOR ANY OTHER APPLIANCE.
This appliance may be installed in an aftermarket permanently located manufactured(mobile) home where not prohibited by
local codes.
This appliance is only for use with thetype of gas indicated on the rating plate.
This appliance is not convertible for use
with other gases unless a certified kit is
used.

Models:SDDVT Series: SDDVTCB, SDDVTEB, SDDVTBS,SDDVTBD, SDDVTBM
12734 SDDVTCSEB,SDDVTC Series: SDDVTCSCB,
Stardance
Dv
SDDVTCSBS, SDDVTCSBD,SDDVTCSBM
cover
8/07

Homeowner’s Installation
and Operating Manual
DE S I GN

C E RT I F I E D

CERTIFI E D

INSTALLER: Leave this manual with the appliance.
CONSUMER: Retain this manual for future reference.
30004968 9/10 Rev. 5

Stardance® Direct Vent/Natural Vent Gas Heater

Table of Contents
PLEASE READ THE INSTALLATION & OPERATING INSTRUCTIONS BEFORE USING APPLIANCE.
Thank you and congratulations on your purchase of a Vermont Castings stove.
IMPORTANT: Read all instructions and warnings carefully before starting installation. Failure to follow these
instructions may result in a possible fire hazard and will void the warranty.
Installation &OperatingInstructions

General Information .............................................................................................................3
Installation Requirements for the Commonwealth of Massachusetts...................................4
Stove Dimensions.................................................................................................................5
Installation Requirements......................................................................................................6		
Locating the Stove................................................................................................................6		Clearance Requirements......................................................................................................6		Parallel & Corner Installation.................................................................................................7		Wall and Ceiling Clearances.................................................................................................7		Hearth Requirements............................................................................................................7		Gas Specifications................................................................................................................8		Air Shutter Setting.................................................................................................................8		Gas Inlet and Manifold Pressures.........................................................................................8		Horizontal Termination - Direct Vent ONLY...........................................................................8		
Vertical Termination - Direct Vent ONLY................................................................................9		
Restrictor Plate Adjustment...................................................................................................9		
Vent Termination Clearances..............................................................................................10		General Venting Information - Termination Location........................................................... 11		Termination Clearances......................................................................................................12		
Venting Requirements - Natural Vent ONLY.......................................................................12		
Venting Requirements and Options - Direct Vent ONLY.....................................................13
Assembly
Install the Optional Fan.......................................................................................................15
Procedures
Venting System Assembly - Direct Vent..............................................................................16		
Install Vent Adapter Pipe.....................................................................................................16
		Side Wall Termination Assembly.........................................................................................17
		
Vent Termination Below Grade............................................................................................19		
Vertical (Through the Roof) Vent Assembly........................................................................19		Selkirk Direct-Temp Metalbestos Direct Vent System.........................................................20
		
Venting System Assembly - Natural Vent............................................................................25
		Install the Vent Pipe............................................................................................................26
		Install the Log Set...............................................................................................................26
		Connect Gas Supply Line...................................................................................................28		
Burner Information..............................................................................................................28
		Install ON/OFF Switch.........................................................................................................28
		
Thermostat Connection (Optional)......................................................................................29
		Receiver Installation - (STDDVTCS Series)........................................................................29
		Install the Front Plate..........................................................................................................29
Operation
Your First Fire......................................................................................................................29
		
Pilot and Burner Information...............................................................................................29		Flame & Temperature Adjustment / Flame Characteristics.................................................30
		Lighting and Operating Instructions....................................................................................31
		
Troubleshooting - SIT NOVA 820 (SDDVT Series) ............................................................32		
Instructions for RCSITEA (SDDVTCS Series).....................................................................33
		Troubleshooting for RCSITEA.............................................................................................36
		Fuel Conversion Instructions...............................................................................................37
Maintenance
Annual System Inspection...................................................................................................40		
Logset and Burner/Cleaning and Inspection.......................................................................40		
Care of Cast Iron.................................................................................................................40		Cleaning the Glass..............................................................................................................40
		
Glass Replacement.............................................................................................................40
		Gasket Replacement...........................................................................................................41
		Inspect the Vent System Annually.......................................................................................41
		
Check the Gas Flame Regularly.........................................................................................41
		
Stove Disassembly..............................................................................................................41		
Wiring Diagrams..................................................................................................................42
Replacement Parts ............................................................................................................................................44
Optional Accessories . .........................................................................................................................................48
Warranty............................................................................................................................................51

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

General Information
The Stardance Direct Vent/Natural Vent Room Heater, ModelNos. SDDVTCB, SDDVTEB, SDDVTBS, SDDVTBD, SDDVTBM,SDDVTCSCB, SDDVTCSEB, SDDVTCSBS, SDDVTCSBD, SDDVTCSBM is a vented gas appliance listed to the ANSI Standard
Z21.88-2009 and CSA 2.33-2009 for Vented Room Heaters, and
CSA 2.17-M91, Gas-Fired Appliances For Use at High Altitudes.
The installation of the Stardance Direct Vent/Natural Vent Room
Heater must conform with local codes, or in the absence of local codes, with National Fuel Gas Code, ANSI Z223.1/NFPA 54— latest edition and CSA B-149.1 Installation Code. (EXCEPTION: Do not derate this appliance for altitude. Maintain the
manifold pressure at 3.5” w.c. for Natural Gas and 10.0” w.c. for
LP gas at maximum input.)
This appliance is only for use with the type of gas indicated on
the rating plate. This appliance is not convertible for use withother gases unless a certified kit is used.
Installation and replacement of gas piping, gas utilizationequipment or accessories, and repair and servicing ofequipment shall be performed only by a qualified agency,
preferably NFI or WETT (Canada) certified. The term “qualified agency” means any individual, firm, corporation, or
company that either in person or through a representativeis engaged in and is responsible for (a) installation or replacement of gas piping, or (b), the connection, installation,
repair, or servicing of equipment, who is experienced insuch work, familiar with all precautions required, and hascomplied with all the requirements of the authority having
jurisdiction.
The Stardance Direct Vent/Natural Vent Room Heater should
be inspected before use and at least annually by a qualified
service agency. It is imperative that control compartments,
burners, and circulating air passageways of the appliancebe kept clean.
The Stardance Direct Vent/Natural Vent Room Heater and its
individual shut-off valve must be disconnected from the gas supply piping during any pressure testing of that system at test pressures in excess of 1/2 psig (3.5 kPa).
The Stardance Direct Vent/Natural Vent Room Heater must be
isolated from the gas supply piping system by closing its individual manual shutoff valve during any pressure testing of thegas supply piping system at test pressures equal to or less than
1/2 psig.
‘Direct Vent’ describes a sealed combustion system in which incoming outside air for combustion and outgoing exhaust enterand exit through two separate concentric passages within thesame sealed vent system. The system does not use room air tosupport combustion. The Direct Vent system permits the gas appliance to be vented directly to the outside atmosphere throughthe side of the house or vertically through the roof. Conventional
venting systems (Natural Vent) take air from the room for combustion and vent the exhaust vertically through the roof to theatmosphere.
This appliance is approved for bedroom installations in the U.S.
and Canada.
This appliance may be installed in an aftermarket* manufactured(mobile) home, where not prohibited by state or local codes.
WARNING: Operation of this heater when not connected to aproperly installed and maintained venting system can resultin carbon monoxide (CO) poisoning and possible death.

30004968

The Stardance Direct Vent/Natural Vent Room Heater, when installed, must be electrically grounded in accordance with local
codes or, in the absence of local codes, with the National Electrical Code ANSI/NFPA 70, (latest edition), or of the current Canadian Electrical Code C22.1.
Due to high temperatures this appliance should be locatedout of traffic and away from furniture and draperies.
WARNING: This appliance is hot while in operation. Keepchildren, clothing, and furniture away. Contact may causeburns or ignition of combustible materials.
Children and adults should be alerted to the hazards of highsurface temperatures and should stay away to avoid burns
or clothing ignition.
Young children should be carefully supervised when they
are in the same room as the appliance. Toddlers, young children and others may be susceptible to accidental contact
burns. A physical barrier is recommended if there are at risk
individuals in the house. To restrict access to a fireplaceor stove, install an adjustable safety gate to keep toddlers,
young children and other at risk individuals out of the room
and away from hot surfaces.
Clothing or other flammable materials should not be placedon or near the appliance.
Any safety screen, glass or guard removed for servicing
an appliance must be replaced prior to operating the appliance.
The appliance area must be kept clear and free from combustible materials, gasoline, and other flammable vapors
and liquids.
The flow of combustion and ventilation air must not be obstructed. The installation must include adequate accessibility and clearance for servicing and proper operation.
WARNING: Do not operate the Room Heater with the glass
panel removed, cracked or broken. Replacement of the panel should be done by a licensed or qualified service person.
Do not use this appliance if any part has been under water.
Immediately call a qualified service technician to inspect theappliance and to replace any part of the control system andany gas control which has been under water.
Do not burn wood, trash or any other material for which thisappliance was not designed. This appliance is designed toburn either natural gas or propane only.
This gas appliance must not be connected to a chimney flue
serving a separate solid-fuel burning appliance.
CAUTION: Label all wires prior to disconnection when servicing controls. Wiring errors can cause improper and dangerous operation.
Verify proper operation after servicing.
* Aftermarket: Completion of sale, nor for purpose of resale, from the
manufacturer.

Proposition 65 Warning: Fuels used in gas, woodburning or
oil fired appliances, and the products of combustion of such
fuels, contain chemicals known to the State of California tocause cancer, birth defects and other reproductive harm.
California Health & Safety Code Sec. 25249.6

Stardance® Direct Vent/Natural Vent Gas Heater

Installation Requirements
Requirements for the Commonwealth of
Massachusetts
All gas fitting and installation of this heater shall only bedone by a licensed gas fitter or licensed plumber.
For all side wall horizontally vented gas fueled
equipment installed in every dwelling, building or
structure used in whole or in part for residential
purposes, including those owned or operated by the
Commonwealth and where the side wall exhaustvent termination is less than seven (7) feet above
finished grade in the area of the venting, including
but not limited to decks and porches, the following
requirements shall be satisfied:Inspection
The state or local gas inspector of the side wall
horizontally vented gas fueled equipment shall not
approve the installation unless, upon inspection, theinspector observes carbon monoxide detectors andsignage installed in accordance with the provisions of
248 CMR 5.08(2)(a)1 through 4.

Exemptions
The following equipment is exempt from 248 CMR
5.08(2)(a)1 through 4:• The equipment listed in Chapter 10 entitledInstallation of Carbon Monoxide Detectors
At the time of installation of the side wall horizontal
vented gas fueled equipment, the installing plumber
or gas fitter shall observe that a hard wired carbon
monoxide detector with an alarm is installed on each
additional level of the dwelling, building or structure
served by the side wall horizontal vented gas fueled
equipment. It shall be the responsibility of the property
owner to secure the services of qualified licensed
professionals for the installation of hard wired carbon
monoxide detectors.
In the event that the side wall horizontally vented gas
fueled equipment is installed in a crawl space or an
attic, the hard wired carbon monoxide detector withalarm and battery back-up may be installed on the next
adjacent floor level.
In the event that the requirements of this subdivision
can not be met at the time of completion of installation,
the owner shall have a period of thirty (30) days
to comply with the above requirements; provided,
however, that during said thirty (30) day period, abattery operated carbon monoxide detector with analarm shall be installed.

Approved Carbon Monoxide Detectors
Each carbon monoxide detector as required inaccordance with the above provisions shall comply with
NFPA 720 and ANSI/UL 2034 listed and IAS certified.

•

MANUFACTURER REQUIREMENTS
Gas Equipment Venting System Provided
When the manufacturer of Product Approved sidewall horizontally vented gas equipment provides aventing system design or venting system components
with the equipment, the instructions provided by the
manufacturer for installation of the equipment and theventing system shall include:• Detailed instructions for the installation of the venting•system design or the venting system components;
and
A complete parts list for the venting system design or
venting system.

Gas Equipment Venting System NOT Provided
When the manufacturer of a Product Approved sidewall horizontally vented gas fueled equipment does
not provide the parts for venting the flue gases, but
identifies “special venting systems”, the following
requirements shall be satisfied by the manufacturer:• The referenced “special venting system” instructions

Signage
A metal or plastic identification plate shall bepermanently mounted to the exterior of the building at
a minimum height of eight (8) feet above grade directlyin line with the exhaust vent terminal for the horizontally
vented gas fueled heating appliance or equipment. The
sign shall read, in print size no less than one-half (1/2)
inch in size, “GAS VENT DIRECTLY BELOW, KEEP
CLEAR OF ALL OBSTRUCTIONS”.

“Equipment Not Required To Be Vented” in the mostcurrent edition of NFPA 54 as adopted by the Board;andProduct Approved side wall horizontally vented gas
fueled equipment installed in a room or structure
separate from the dwelling, building or structureused in whole or in part for residential purposes.

•

shall be included with the appliance or equipment
installation instructions; andThe “special venting systems” shall be ProductApproved by the Board, and the instructions forthat system shall include a parts list and detailed
installation instructions.

A copy of all installation instructions for all ProductApproved side wall horizontally vented gas fueled
equipment, all venting instructions, all parts lists
for venting instructions, and/or all venting design
instructions shall remain with the appliance orequipment at the completion of the installation.
30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Stardance Direct Vent / Natural Vent Dimensions
7" Outer Dia.
(178 mm)
Supply Inlet

126 ”(321 mm)

Flue Collar C
L

2(6 ”(73 mm)

9"(229 mm)126 ”(321 mm)CL

7" Outer Dia.
(178 mm)
Supply Inlet

2(6 ”(73 mm)8"(203 mm)

Flue Collar
CL

SDDVT Models

86M"(222 mm)

SDDVTC Models

266M"(680 mm)

76M”(197 mm)

Supply Inlet

CL

3"(76 mm)1456O"(355 mm)

2556O"(648 mm)Fig. 1 Stardance dimensions.

12734
Stardance dim
Attention
8/07 djt

The Stardance stove is shipped from the factory as a Direct Vent Gas Heater. This heater
may be converted into a Natural Vent unit in the field. If a Natural Vent heater is desired,
the Vermont Castings Z31B00 FSDHAG Draft Hood must be directly installed to the topof the unit according to the installation instructions. The Draft Hood Adapter is available
in the 7FSDHASK stove kit or as a separate item.
When the Stardance stove is converted to Natural Vent, it uses 4” vent pipe. For aesthetic purposes the MHSC direct vent system may be used up to the ceiling.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Installation Requirements
The installation must conform with local codes or, in
the absence of local codes, with the National Fuel Gas
Code, ANSI Z223.1/NFPA 54 - latest edition. (EXCEPTION: Do not derate this appliance for altitude. Maintain the manifold pressure at 3.5 inches w.c. for NaturalGas, and 10 inches w.c. for Propane).
In Canada, installation must be in accordance with thecurrent CSA B-149.1 Installation Codes and/or local
codes.
The installation should be done by a qualified service person who is familiar with the building codes
and installation techniques appropriate for yourarea to accomplish a safe and effective installation.
Your dealer or your local gas supplier will be able torefer a qualified service person.
WARNING: Due to high temperatures, theHEATER should be located out of traffic
and away from furniture and draperies.
The surface of the Heater Is hot when it is in use.
Young children should be watched carefully when
they are in the same room when the Heater is inuse, and they should be taught to avoid the hot
surface. Keep any objects that can burn well awayfrom the Heater, and observe the recommended
clearances that follow.

 7!2.).'(/4 ',!33 7),,#!53% "52.3
$/ ./4 4/5#( ',!33
5.4), #//,%$
.%6%2 !,,/7 #(),$2%.
4/ 4/5#( ',!33

Locating the Stove
In choosing a location for the stove, consider:•		The location of outside walls;•		Where additional heat is needed:•		Where family members gather most often;•		The vent system requirements.
NOTE: We do not recommend the use of wallpaper
next to this stove. Over time, radiant heat may cause
the wallpaper to shrink, or may adversely affect thebinders in the wallpaper adhesive.



A

D
B
C
E

ST207

Fig. 2 Possible stove locations.
ST207aClearance
Requirements
Stardance
Stove locations
Minimum Clearances
to Combustible
9/28/00 djt
Materials
Measure side clearances as shown in Figures 3 and 4
from the outer edge of the cast iron stove top. Measurerear clearances from the outermost surface of the steel
rear skirt.
The Stardance heater is approved for installation into
an alcove constructed of combustible materials to thedimensions and clearances shown on the next page.
The same clearances apply in a standard parallel installation.

Warning:• Always maintain required clearances(air spaces) to nearby combustibles to prevent
fire hazard. Do not fill air spaces with insulation. All venting components must maintain a1” (25 mm) clearance to combustible materials.
Maintain a 6” (150 mm) clearance when using asingle wall pipe.
•		The gas appliance and vent system must be
vented directly to the outside of the building
and never be attached to a chimney serving aseparate solid fuel or gas-burning appliance.
Each direct vent appliance must use its own
separate vent system. Common vents are prohibited.
• 		Refer to the manufacturer’s instructions included with the venting system for complete
installation procedures.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Parallel Installation: Minimum Clearanceand Flue Centerline, Direct Vent andNatural Vent

Wall Centerline from Floor
Direct Vent Only

C
L
C

A

D

A

C
L

B
ST131b
ST128b

Stove Clearances:

A: 4” (102 mm)
B: 4” (102 mm)
Pipe Centerlines:
C: 15Z\x” (395 mm)
ST128b
D: 9” (229 mm)
Fig. 3 Parallel installation,
minimum back and side clearStardance
ances, and flue centerlines.

flue centerline
9/28/00
djt
Corner
Installation:

Effective Minimum
Wall Thimble56” (1480 mm) (MHSC Pipe)
Centerline
52” (1378ST131bmm) (Simpson Duravent Pipe)
Stardance
Fig. 5 Minimum wall thimble centerline.
wall thimble
9/28/00 djt

Wall and Ceiling Clearances
D

Minimum Clearance and Flue Centerline,
Direct Vent and Natural Vent
B

B

C

A

A

B

ST101bA
ST129b

Stove Clearance:
Pipe Centerline:

A: 4” (102 mm)
B: 14Z\x” (370 mm)

Fig. 4 Corner installation, minimum corner clearance and flue
centerline.
ST129bStardancecorner specs
9/28/00 djt
30004968

A: Rear Wall4” (102 mm)
B: Min. Clearance
45Z\v” (1154 mm)*
C: Min. Alcove Height72” (1830 mm)
ST101b
D: Stardance
Max. Alcove Depth48” (1220 mm)
SidewallClearance4” (102 mm)
Direct Vent
Fig. 6 Dimensions
andclearancestoceiling or alcove.
Min. Clrnc
9/28/00 djt

Hearth Requirements

The Stardance Heater must be installed on rigid flooring. When the heater is installed directly on any combustible surface other than wood flooring, a metal orwood panel extending the full width and depth of theunit must be used as the hearth. There are no otherhearth requirements.
Stardance® Direct Vent/Natural Vent Gas Heater
Gas Specifications

Horizontal Termination Direct Vent ONLY

				

Max.
Min.
				
Input Input
Model
Fuel
Gas Control
BTU/h BTU/hSDDVT Series
Nat Millivolt Manual	28,000	20,000
SDDVT Series
Prop Millivolt Manual	28,000	20,000
SDDVTCS Series Nat
Millivolt Hi/Lo	28,000	20,000
SDDVTCS Series Prop Millivolt Hi/Lo	28,000	20,000

Air Shutter Setting
Minimum rear injector air inlet openings.
Model
Natural Gas
LP
Direct Vent
1/2” Open1/2” OpenNatural Vent
1/2” Open1/2” Open
Weight: Fully assembled; 202 lbs.

The vent must rise vertically a minimum of 24” (610 mm)
off the top of the unit, before the first elbow. The horizontal run may extend up to 20’ (6 m) and include a verticalrise of up to 40’ (12 m). (Fig. 7) Horizontal terminationmust also meet the criteria shown in Figures 9 through11.
• Approved vent systems must terminate above and including the heavy line in Figure 7.
• Two 45° elbows may be substituted for each single
90° elbow.
• With a rise between 2’ - 5’, one 90° or two 45° elbows
may be used.

Gas Inlet and Manifold Pressures
LP (Propane)11.0” w.c.
14.0” w.c.
10” w.c.

Stardance Direct Vent / Natural Vent
Certified to:
ANSI Z21.88-2009 / CSA 2.33-2009
Vented Gas Fireplace Heaters
The installation of your Vermont Castings stove must
conform with local codes, or in the absence of local
codes, with the National Fuel Gas Code ANSI Z223.1/
NFPA 54 - latest edition, or CSA B149.1 Installation
code. (EXCEPTION: Do not derate this appliance for
altitude up to 4,500 feet (1,370m). Maintain the manifold pressure at 3.5” w.c. for Natural Gas and 10.0”
w.c. for LP Gas.

High Elevations
Input ratings are shown in BTU per hour and are certified without deration for elevations up to 4,500 feet
(1,370m) above sea level.
For elevations above 4,500 feet (1,370m) in USA,installations must be in accordance with the current
ANSI Z223.1/NFPA 54 and/or local codes having
jurisdiction.
In Canada, please consult provincial and/or local authorities having jurisdiction for installations at elevations above 4,500 feet (1,370m).
WARNING: Improper installation, adjustment,
alteration, service or maintenance can cause injury or property damage. Refer to this manual forcorrect installation and operational procedures.
For assistance or additional information consult
a qualified installer, service agency, or the gas
supplier.


40
39
38
37
36

Vertical Run (in feet)

Natural5.5” w.c.
14.0” w.c.
3.5” w.c.

(Measured from the appliance flue collar to the top of the vent pipe.)		
Inlet Minimum
Inlet Maximum
Manifold Pressure

35
34
33

May use up to
three 90° Elbows

32
31
30
29
28
27
26

ST134a
FDV28
Horizontal
vent run
12/3/99 djt
areas modified
1/11/00 djt

25
24
23
22
21
20
19
18
16
15
14
13
12
11
10
9
8
7
6
5
4
3

One 90°
Elbow

Unacceptable
Venting Configureation

2
1
0
1 2

3

4

5

6

7

8

9 10 11 12 13 14 15 16 17 18 19 20

Horizontal Run (in feet)

ST134aFig. 7 Horizontal vent termination window.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Restrictor Plate Adjustment
for Extended Pipe Runs

Vertical Termination - Direct Vent ONLY
A vertical vent system must terminate no less than 8’(2.44 m) and no more than 40’ (12 m) above the appliance flue collar. A restrictor plate (supplied) must be
used where specified in all vertically terminated ventsystems. (Fig. 8) NOTE: The restrictor plate suppliedwith the vertical termination should be discarded.
Adjust the restrictor plate according to recommendations in Figure 10. A vertically terminated ventsystem must also conform to the following criteria:• No more than three 90° elbows may be used.
• Two 45° elbows may be substituted for one 90°
elbow. No more than six elbows may be used.
• Vent must rise a minimum of 2 feet before offset isused.
• Termination height must conform to roof clearance
as specified in Figure 9.
{ä
Î
În
ÎÇ

All Vertical Terminations in this area
Require use of the
Restrictor Plate*

Vertical Run (in feet)(Measure from the appliance flue collar to the top of the vent pipe.)

ÎÈ
Îx
Î{
ÎÎ

The Stardance stove is shipped with a restrictor platein the Parts Bag. Adjustments can be made by loosening the adjustment screw to allow the restrictor plate toslide up or down. (Fig. 9) A guide for usage is shown in
Figure 10.
NOTE: Some installations may require some adjustment by the installer for optimum flame appearance.
Optimum flame appearance is a flame that is not subject to tall, dirty yellow flames producing soot or flames
lifting off of the ember bed ports.
Restrictor Plate Adjustment
1. Remove the logs if installed.
2. Remove the adjustment screw in the back wall of thefirebox.
3. Install restrictor plate as shown in Figure 9 with
angle on plate on the top right side. Secure withadjustment screw.
4. Adjust restrictor according to examples in Figure 10.
5. Install logs following log installation instructions.

Restrictor Plate

ÎÓ
Î£
Îä
Ó
Ón
ÓÇ
ÓÈ
Óx

Vertical Terminations
must be within this
area

Ó{
ÓÎ
ÓÓ

ST132b
FDV28
Verticalvent run
1/08

Ó£
Óä
£
£n
£È
£x
£{

ST936

Unacceptable Venting
Configuration£Î£ÓFig. 9 SDDVT/SDDVTCS restrictor plate.

££
£ä

34
3$$64 RESTRICTOR PLATE
Examples for Extended
Run/Restrictor Plate Settings



n
Ç
È

No Restrictor
Plate

1. Vertical 40’ (12 m) - restrictor plate lowered completely
down
2. Vertical 20’ (6 m), 90° elbow, 8’ (2.4 m ) horizontal restrictor plate lowered completely down
3. Vertical 10’ (3 m), 90° elbow, 2’ (305 mm) horizontal- restrictor plate lowered completely down

x
ÊÊ{
ÊÊÎ
Ó
£
ä
£

Ó

Î

{

x

È

Ç

n 

£ä ££ £Ó £Î £{ £x £È £Ç £n £

Horizontal Run (in feet)ÓäFigure 10

ST132b

Fig. 8 Vertical vent termination window.
*The restrictor Plate is used on Direct Vent Installations
Only.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Vent Termination Clearances
When planning the installation, consider the locationof the vent terminal and clearances. Some of the mostcommon clearances to keep in mind are shown in
Figure 11.
Important: All vent clearances must be maintained.
Check your vent termination clearances against
Figures 11 through 13.
The vent should be placed so that people cannot beburned by accidentally touching the vent surfaces when
the stove is operating.
The vent termination should be located where it cannot
be damaged by such things as automobile doors, lawn
mowers or snowblowers and it should be located awayfrom areas where it could become blocked by snow,
etc.
Some considerations are:
• Obstructions or impediments to venting.
• Nearby combustible materials that could come into
contact with combustion exhaust gases.
• Other nearby openings {within 12” (305 mm)}through which exhaust gas could reenter the building.
• All vegetation within 3’ (76 mm) that may interferewith the draft.
Other factors that influence where the installation will
be sited include the location of outside walls, where
additional heat may be desired in the home, where thefamily members gather most regularly, and perhaps
most importantly, the distance limitations of the venting
system.

Your stove is approved to be vented either through theside wall, or vertical through the roof.
• MHSC does not require any opening for inspectionof vent pipe.
• Only MHSC and Simpson DuraVent venting components specifically approved and labelled for thisstove may be used.
• Minimum clearances between vent pipes and combustible materials is one (1”) inch (25 mm), except
where stated otherwise.
• Venting terminals shall not be recessed into a wall orsiding.
• Horizontal venting must be installed on a level plane
without an inclining or declining slope.
There must not be any obstruction such as bushes,
garden sheds, fences, decks or utility buildings within
24” from the front of the termination hood.
Do not locate termination hood where excessive snowor ice build up may occur. Be sure to check vent termination area after snow falls, and clear to prevent accidental blockage of venting system. When using snow
blowers, make sure snow is not directed towards venttermination area.

Location of Vent Termination
It is imperative the vent termination be located observing the minimum clearances as shown on this page.

IMPORTANT
Direct Vent Only
• The horizontal termination must not be recessed
into the exterior wall or siding.
• Horizontal vent runs must be level toward the venttermination.
• Clearances around the vent termination must be
maintained.
• For installations using Simpson DuraVent pipe,
parallel installations with minimum wall clearance
have restricted access for connecting the Horizontal Vent Cap straps to the vent pipe. See themaker’s instructions for recommended installation
procedures.

10

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
General Venting Information - Termination Location
INSIDECORNER DETAIL
G
V

N

H

A

D

L

V

E
C
B

V
F

B
Fixed
ClosedOpe

V
B

CFM145a

V VENT TERMINATION

		

B

V

Operable

rable

B

V

V

Fixed
ClosedB

J

X

X AIR SUPPLY INLET

M
I

A

V

K

X

AREA WHERE TERMINAL IS NOT PERMITTEDCanadian Installations1

US Installations2

A = Clearance above grade, veranda, porch,12” CFM145a(30cm)		
12” (30cm)
DV Termin Location		
deck, or balcony
5/01/01 Rev. 12/05/01
sta
B = Clearance to window or door that may be6” (15cm)
for appliances6” (15cm) for appliances		
opened< 10,000Btuh (3kW), 12” (30cm)< 10,000 Btuh (3kW), 9”
			
for appliances > 10,000 Btuh (3kW) and(23cm) for appliances > 10,000
			< 100,000 Btuh (30kW), 36” (91cm)
Btuh (3kW) and < 50,000 Btuh			
for appliances > 100,000 Btuh (30kW)(15kW), 12” (30cm) for					
appliances > 50,000 Btuh (15kW)
C = Clearance to permanently closed window12” (305mm) recommended to12” (305mm) recommended to			prevent window condensation
prevent window condensation
D = Vertical clearance to ventilated soffit located		
above the terminal within a horizontal
18” (458mm)		
18” (458mm)
		
distance of 2’ (610mm) from the center		line of the terminal
E = Clearance to unventilated soffit12” (305mm)		
12” (305mm)
F = Clearance to outside corner
see next page		
see next page
G = Clearance to inside corner (see next page)
see next page		
see next page
H = Clearance to each inside of center line
3’ (91cm) within a height of 15’ (5m)
3’ (91cm) within a height of 15’
		extended above meter/regulator assembly
above the meter/regulator assembly(5m) above the meter/regulator
					
assy
I = Clearance to service regulator vent outlet
3’ (91cm)		
3’ (91cm)
J = Clearance to nonmechanical air supply inlet 6” (15cm) for appliances < 10,000
6” (15cm) for appliances		
to building or the combustion air inlet to any Btuh (3kW), 12” (30cm) for< 10,000 Btuh (3kW), 9”		other appliances
appliances > 10,000 Btuh (3kW) and(23cm) for appliances > 10,000
			< 100,000 Btuh (30kW), 36” (91cm)
Btuh (3kW) and < 50,000 Btuh			
for appliances > 100,000 Btuh (30kW)(15kW), 12” (30cm) for					
appliances > 50,000 Btuh (15kW)
K = Clearance to a mechanical air supply inlet
6’ (1.83m)		
3’ (91cm) above if within 10					feet (3m) horizontally
L = Clearance above paved sidewalk or paved 7’ (2.13m)†		
7’ (2.13m)†		driveway located on public property
M = Clearance under veranda, porch, deck or
12” (30cm)*		
12” (30cm)*
		balcony				N = Any other obstruction within a horizontal distance of 18” (450mm).
1 In accordance with the current CSA-B149 Installation Codes
	2 In accordance with the current ANSI Z223.1/NFPA 54 National Fuel Gas Codes† A vent shall not terminate directly above a sidewalk or paved driveway which is located between two single family dwellings and 		serves both dwellings* only permitted if veranda, porch, deck or balcony is fully open on a minimum 2 sides beneath the floor:
NOTE: 1. Local codes or regulations may require different clearances.
		2. The special venting system used on Direct Vent units are certified as part of the appliance, with clearances tested and 				
approved by the listing agency.
		
3. MHSC assumes no responsibility for the improper performance of the appliance when the venting system does not 			meet these requirements.

Fig. 11 Vent termination clearances.

30004968

11

Stardance® Direct Vent/Natural Vent Gas Heater
Termination Clearances
Termination clearances for buildings with combustible and noncombustible exteriors.
Alcove Applications*
Inside Corner
Outside CornerG=
Combustible
6" (152 mm)

G

F=
Combustible
6" (152 mm)
Noncombustible2" (51 mm)

V

Noncombustible2" (51 mm)

V

C
V

E
O

F

Balcony with perpendicular side wall

Balcony with no side wall

DC

E = Min. 6” (152 mm) for
non-vinyl sidewalls
Min. 12” (305 mm) for
vinyl sidewalls
O = 8’ (2.4 m) Min.

M

M

No.
of Caps		
DMin.		 CMax.
1
3’ (914 mm)	2 x DActual	2	
6’ (1.8 m)
1 x DActual3
9’ (2.7 m)	2/3 x DActual
412’ (3.7 m)
1/2 x DActual

V

V

P
Combustible &Noncombustible

M=
Combustible &Noncombustible12" (305 mm)

M = 24" (610 mm)
P = 20” (508 mm)

DMin. = # of Termination caps x 3
CMax. = (2 / # termination caps) x DActual

584-15*NOTE: Termination in an alcove space (spaces open only on one side and with an overhang) is permitted with the dimensions
specified for vinyl or non-vinyl siding and soffits. 1. There must be a 3’ (914 mm) minimum between termination caps. 2. All
mechanical air intakes within 10’ (1 m) of a termination cap must be a minimum of 3’ (914 mm) below the termination cap. 3. All
gravity air intakes within 3’ (914 mm) of a termination cap must be a minimum of 1’ (305 mm) below the termination cap.

Fig. 12 Termination clearances.

Vertical Run (in feet)(Measured from top of the unit before any elbow)

Venting Requirements - Natural Vent Only
ÎÈ
Î{
ÎÓ
Îä

Venting RunsA

NOTE: When venting staight vertical, without any
elbow, a minimum of 8 ft. vertical is required
off the top of the stove.

B

Ón
ÓÈ

= Acceptable venting configuration

Ó{= Unacceptable venting configurationÓÓÓä

A: Vertical installations up to 36 feet (12m) inheight. Up to an 18 ft. horizontal vent run can beinstalled within the vent system using amaximum of two 90-degree elbows or four
45-degree elbows.

£n
£È
£{
£Ó
£ä

B: Vertical installations up to 36 feet (12m) inheight. Up to a 24 ft. horizontal vent run can beinstalled within the vent system using amaximum of two 45-degree elbows.
(Ratio = 2/3, Hor./Vert.)nÈ{Ó£ÊÊÊÓÊÊÊ{ÊÊÊÊÊÈÊÊÊÊnÊÊÊÊ£äÊÊ£ÓÊ£{ÊÊ£ÈÊÊ£nÊÊÊÓäÊÊÓÓÊÊÓ{Horizontal Run (in feet)

NOTE: When using the FSDHAG, the restrictor plate
supplied with the stove is not used.

Fig. 13 Vent termination window - Natural Vent ONLY.

12

FP567
NVBR/NVBC VENTING RUNS
11/12/97

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Venting Requirements and Options Direct Vent ONLYApproved Vent System Components
The Stardance Heater must be vented to the outdoors
through an adjacent exterior wall or through the roof.
The venting system must be comprised of the appropriate listed venting components specified on this page.
These parts are available from DuraVent Corporation,
Selkirk Corporation or your Vermont Castings Dealer.
See Figure 4 for dimensions relevant to the standard
minimum-vent kits.
Simpson DuraVent Components
www.duravent.com
Phone: 1-800-835-4429, Fax: 1-707-446-4740
Minimum Horizontal Vent Kit
2792
Starter Pipe Assembly (incl. inner & outer sections)	2768*
90° Elbow, Blk.
46DVA-E90B*
45° Elbow, Gal.
46DVA-E45
6” Straight, Blk.
46DVA-06B*
9” Straight, Blk.
46DVA-09B
11” - 14⁵⁄₈” Adjustable Straight Section
46DVA-08AB12” Straight
46DVA-12
24” Straight
46DVA-24B*
36” Straight
46DVA-36B
48” Straight
46DVA-48
Horizontal Vent Cap
46DVA-HC*
Wall Plate
46DVA-DC
Vinyl Siding Shield
46DVA-VSS
Snorkel Termination - 14”
46DVA-SNK14
Snorkel Termination - 36”
46DVA-SNK30
Wall Strap
46DVA-WS
Cathedral Ceiling Support Box
46DVA-CS
Storm Collar
46DVA-SC
Firestop Spacer
46DVA-FS
Flashing 0/12 - 6/12	
46DVA-F6
Flashing 6/12 - 12/12	
46DVA-F12
Steel Chimney Conversion Kit
Kit A (6B\,” - 8B\,”)
46DVA-KCA
Kit B (6B\,” - 10Z\x”)
46DVA-KCB
Kit C (6B\,” - 13”)
46DVA-KCC
Masonry Chimney Conversion Kit
46DVA-KMC
Vertical Termination Cap (High Wind)46DVA-VCH
Vertical Termination Cap (Low Profile)
46DVA-VC

Selkirk Corporation Vent Components
www.selkirkcorp.com
1301 W. President George Bush Highway Ste. 330
Richardson, TX 75080
Phone: 1-800-992-8368, Fax: 1-877-393-4145
Appliance Adapter
90° Elbow, Blk.
45° Elbow, Blk.
6” Straight, Blk.
9” Straight, Blk.
4” - 10” Adjustable Straight Section Blk.
12” Straight, Blk.
18” Straight, Blk.
24” Straight, Blk.
36” Straight, Blk.
48” Straight, Blk.
Horizontal Termination
Wall Thimble
Vinyl Siding Standoff
Snorkel Termination - 14”
Snorkel Termination - 36”
Wall Support Band
Cathedral Ceiling Support Box
Storm Collar
Firestop Spacer
Flashing 0/12 - 6/12	
Flashing 6/12 - 12/12	
Steel Chimney
Horizontal Kit A
Horizontal Kit B
Vertical Kit
Masonry Chimney Kit
Vertical Termination Cap

4DT-AAV
4DT-EL90B
4DT-EL45B
4DT-06B
4DT-09B
4DT-AJ12B
4DT-12B
4DT-18B
4DT-24B
4DT-36B
4DT-48B
4DT-HC
4DT-WT
4DT-VS
4DT-ST14
4DT-ST36
4DT-WS/B
4DT-CCS
4DT-SC
4DT-FS
4DT-AF6
4DT-AF12
4DT-HKA
4DT-HKB
4DT-VKC
4DT-MCK
4DT-VC*Included in Minimum Horizontal Vent Kit #2792

All DuraVent Straight vent pipe sections have a net
length 1Z\x” (37mm) less than the nominal dimension;i.e., a 6” (152mm) Straight pipe section has an effective
length of 4Z\x” (115mm).

NOTE: Direct vent pipe may be used on the Natural
Vent system from the top of the draft hood adapter tothe ceiling.

30004968

13

Stardance® Direct Vent/Natural Vent Gas Heater
MHSC Vent Components
The following kits are available to meet the needs ofmost installations. All pipe has a 7” outer diameter andincludes a 4” diameter inner section. A (CG) designation indicates the part is finished in Charcoal Gray paint.
Consult your dealer about other vent parts that may beappropriate to complete the installation.
Min. Through the Wall Vent Kit
7TFSSK(1) 90-Degree Elbow (CG)(1) 24” Straight pipe (CG)(1) 24” - 42” Adjustable Straight Pipe
(1) Side Wall Termination(1) Firestop(1) Zero-clearance sleeve(1) Hardware package(1) Finishing plate (CG)(1) Finishing collar (CG)(4) Charcoal Gray flue pipe rings
Starter Kit for Below Grade Installation
7TDVSKS(1) Snorkel Termination (7TDVSNORK)
Vertical Termination Kit, 1/12-6/12 Pitch
7TDVSKVA(1) Combination Horizontal Offset / Roof Support(1) Vertical Termination(1) Storm Collar(1) 1/12-6/12 Flashing(1) Finishing Plate (CG)(1) Finishing Collar (CG)
(1) Polished Brass Flue Pipe Ring
(1) Hardware Package
Vertical Termination Kit, 7/12-12/12 Pitch
7TDVSKVB(1) 7/12 - 12/12 Flashing
and all of the other Vertical Termination parts.
Vertical Termination, Flat Roof7DVSKVF(1) Flat Flashing
and all of the other Vertical Termination parts.

Twist Lock 12” Straight Pipe (CG)
7TFSDVP12(1) 12” Non-adjustable Pipe
Twist Lock 12”-18” Straight Pipe (CG)
7TFSDVP1218(1) 12” - 18” Adjustable Pipe
Twist Lock 24” Straight Pipe (CG)
7TFSDVP24(1) 24” Non-adjustable Pipe
Twist Lock 48” Straight Pipe (CG)
7TFSDVP48(1) 48” Nonadjustable Pipe
Twist Lock 45-Degree Elbow (CG)
7TFSDVT45
for vertical offsets(1) 45-degree Elbow
Draft Hood Adapter
FSDHAG
NV Stove Kit
7FSSK(1) 7” Diameter Polished Brass Trim Ring
(1) 48” Nonadjustable Pipe (CG)(1) 24” Nonadjustable Pipe (CG)(1) Finishing Plate(1) Finishing Collar (CG)(1) 90 Degree Elbow (CG)Stove Kit
7FSDHASK
Includes all parts in the 7FSSK plus the Draft Hood Adapter
FSDHAG
Combination Offset/Roof Support
7DVCS
Attic Insulation Shield
7DVAIS
7” Charcoal Gray Pipe Rings, (4)7FSDRG
7” Polished Brass Pipe Rings (4)7FSDRP
Wall Thimble
942G

NOTE: Direct vent pipe may be used on the Natural
Vent system from the top of the draft hood adapter tothe ceiling.

14

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Install the Optional Fan - SDDVT Series
If you are installing the optional convection Fan Kit#2767 (FK26), continue here. If you are not installing a
Fan Kit, go to Page 16, Venting System Assembly.
1. The fan kit includes a Blower Assembly and a Rheostat Assembly, connected by a cable. (Fig. 14) The
Blower Assembly mounts to the bottom rear of thestove, and the Rheostat mounts to the valve bracket
to the left of the valve. The assembly includes a‘snapstat’ which automatically turns the fan On (orOff) above (or below) approximately 109°. The Rheostat also provides a range of fan speed settings fromOff (which overrides the snapstat function) to High.
Unpack and inspect the Blower assembly. Confirm
the fan spins freely.

• Insert the rheostat through the hole in the back•••of the left side of the valve bracket, aligning thelocator pin with the smaller hole in that bracket.
Thread the retaining nut onto the shaft of therheostat, tightening with a wrench. Do not overtighten.
Attach the control knob to the rheostat shaft.
Use the wire tie to secure the fan and rheostat
wire harnesses together.

Rear Skirt
Sheet Metal
ScrewsWARNING
This appliance is equipped with a three-prong(grounded) plug for your protection against shock
hazard and should be plugged directly into a properly grounded three-prong receptacle. Do not cut or
remove the grounding prong from this plug.

Not Used on
Stardance

Snapstat
BracketSnapstat/
Extension
Assembly

Rheostat
Assembly

Rear Skirt
InsertST313

Fig. 15 Remove rear skirt insert.
Star Washer
Sheet Metal Screws
Phillips
Pan Head
Bolts

1

2

Star
Washer

ST313
fk26
install fan kit
rear skirt insert
1/24/00
3

BlowerAssembly
ST473aFig. 14 Fan kit components.

2. Remove the rear skirt insert panel at the bottom of
the Rear Skirt (Fig. 15) and fasten the blower assemST473a
bly to the firebox backwith the two Phillips pan-head
Fan parts#2767 FK26
bolts originally installedin the firebox back. (‘1’, Fig.
9/29/00
16)
3. Attach the snapstat assembly to the snapstat bracket
with two sheet-metal screws. (‘2’, Fig. 16) Attach thesnapstat bracket to the stove with a hex-head bolt
passing through the bracket and into the stove base.
(‘3’, Fig. 16)
4. The rheostat control switch attaches to the left sideof the valve bracket at the front of the stove. (Fig. 17)• Remove retaining nut from shaft of rheostat. (ifpreinstalled)
30004968

NOTE: Shown
without shell forclarification

Snapstat
1/4” - 20
Hex Bolt

Snapstat
BracketST314

Fig. 16 Attach the fan assembly and the snapstat.

ST314
Fk26ceattach fan
Rheostat Retaining
1/24/00
CollarRheostat Knob

ST347aFig. 17 Attach the fan rheostat.

ST347aJUV
FK28
rheostat install
9/21/00

15

Stardance® Direct Vent/Natural Vent Gas Heater
Venting System Assemlby - Direct Vent
General Information
The Stardance is approved for installation only with thevent components listed on Pages 13 & 14. Follow thevent component instructions exactly.
For U.S. installations: The venting system must conform with local codes and/or the current National Fuel
Gas Code, ANSI Z223.1/NFPA 54.

ENT

CEM

For Canadian installations: The venting system must
conform to the current CSA B149.1 installation code.

Install the Vent Adapter Pipe
(MHSC Vent Components)
1. Attach Inner Starter Pipe, (found in the partsbag), to the next section of inner pipe.
• Run a bead of sealant about 1/2” from the upper
end of the Inner starter pipe and join the two sections
together.
• Drill three pilot holes into the Inner Starter andsecure the assembly with three sheet metal screws.
(Fig. 18)

ST212aFig. 19 Attach inner assembly to flue collar.

ST212aattach inner assy
no restrictor plate
6/07 djt

First Section of Vent
Pipe
#8 x 1/2” Sheet
Metal Screws
ST213

ENT

3” Inner
Starter PIpe

CEM

Fig. 20 Fasten outer pipe with #12 x 1/2” sheet metal screw.

ST211

Fig. 18 Connect the inner starter with the next section of inner vent pipe.

2. Dry fit the Inner Pipe assembly to the stove forthe purpose of determining the center line of thepipe on the wall.
• Side Wall Terminations: Dry fit the outer elbow
with the vertical outervent and confirm the centerline
ST211
alignment with the attachwall thimble
inneropening.
pipe
3. Attach the Inner Vent
Assemblyto next sectionto the stove.
• Run a bead of sealantaround12/4/99
djt the bottom end of
the starter pipe and attach the assembly to the stove
using three 1/4-20 x 3/8” Phillips screws provided in
the parts bag. (Fig. 19)
4. Install the Outer Adapter Pipe. Apply a 1/4” beadof cement around the inside wall of the pipe, about1” from the end. Insert the pipe over the stove flue
collar, keeping the vertical seam oriented to the backof the stove. Also, be sure to align holes on the pipewith the holes on the flue collar of the firebox. Fasten
the pipe to the holes in the flue collar with the #12 x
1/2” sheet metal screws provided. (Fig. 20)
16

Install the Vent Adapter Pipe
(Simpson Dura-Vent Components)
1. Discard the inner
starter pipe shipped with the
ST213
stove. Using thestarter
pipeadpaterassembly listed on
installouterPage 7, slide theinnersectionout to allow access.
12/6/99 djt• Run a bead of sealant around the bottom end of
the starter pipe and attach the assembly to the stove
using three 1/4-20 x 3/8” Phillips screws provided in
the parts bag. (Fig. 21)
2. Install the Outer Adapter Pipe. Apply a 1/4” bead of
cement around the outside surface, about one inch
from the crimped end. (Fig. 22) Orient the verticalseam to the rear, and insert the crimped end of theouter pipe into the flue collar. Fasten with three sheet
metal screws provided.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Secure with a minimum of two #8 x 1/4” sheet metalscrews and seal with hi-temp silicone.

Inner Adapter
Pipe

1/4-20 x
3/8 Phillips
ScrewsFor units factory equipped with appliance adapters fromother brands of Direct Vent systems, it is permissible
to simply slide a length of DT pipe over the applianceadapter. Secure with a minimum of two #8 x 1/4” sheet
metal screws and seal with hi-temp silicone.

ENT

CEM

Side Wall Termination Assembly

ST355b

Fig. 21 Simpson Dura-Vent - install inner adapter pipe.

1. Locate the vent opening on the wall. Refer to Page
7, Figure 6, to determine the opening centerline.
It may be necessary to first position the stove andmeasure to find the hole location. Depending onwhether the wall is made of combustible materials,
cut the opening to the size shown in Figure 24. Combustible wall openings must be framed as shown in
Figure 23.
MHSC System

ST355bdura ventattach inner assy
no restrictor plate
6/07 djt

9C\,”(240mm)

9C\,”(240mm)

ST356aDuraVent
SystemCombustible Wall
10”(254 mm)

Framing DetailFig. 22 Simpson Dura-Vent - install outer adapter pipe.
7Z\x”(191 mm)

Install Vent Adapter Pipe
(Selkirk Corporation Vent Components)
The appliance adapter (AA) adapts DIRECT-TEMP to
most direct vent appliances incorporating outlet collars configured
to receive most common 4” (ID) by 6B\,”
ST356(OD) or 5” (ID)by
(OD) “Twist Lock” style, direct ventdura8”ventsystems.

attach outer assy

The adapter incorporates
4/7/00 djt two indentations on the outerwall of the inlet end, which are designed to “Twist Lock”
into place upon attachment to the appliance outlet. Alignthe adapter indentations with the entry slots of the appliance outlet and slide together. Turn the adapter clockwise approximately one-quarter turn to lock in place.
The outlet end of the adapter is standard DIRECTTEMP construction.
For connection of Direct-Temp to units with 4” x 7” flue
outlets, the following methods have been approved:• Install the Universal/Napoleon Appliance Adapter
4DT-AAN.

• Connect a standard Direct-Temp pipe length (donot use an adjustable length in this application) a
minimum of 1Z\x” over the flue outlet. The outside of
the Direct-Temp Length will fit inside the flue outlet
30004968

VO584-100

Noncombustible Wall

Fig. 23 Locate vent opening.

2. Measure the wall thickness and cut the wall sleevesections to proper length (MAXIMUM 12”). Assemble
the sleeve with the #8 sheet metal screws supplied.
Attach the firestop plate to the sleeve end with theholes. (Fig. 24) NOTE: The wall sleeve is required
VO584-100in combustible walls only.
Vent Opening
3. Install the Wall Firestop/Sleeve assembly into the
2/99thedjt
wall cutout and fasten
firestop to the wall cutout
framing members. (Fig. 24)
For DuraVent pipe only: Install vent pipe by aligning
the locking system together, sliding the pipes together and twisting clockwise.
• Install 90° elbow. Twist lock as before.
• Slide the wall plate over horizontal run before attaching the horizontal run to the elbow. Fasten wall
plate to wall.
4. For MHSC Vent Pipe only: If necessary, measure
to determine the vertical length (X) of pipe required
from the adapter pipe to the wall cutout centerline,
17

Stardance® Direct Vent/Natural Vent Gas Heater
12”(305 mm)Max. Length

SleeveX#8 Sheet
Metal Screws

ST215

Fig. 26 Measure the horizontal length.

Firestop
ZCS103Fig. 24 Assemble the wall sleeve and firestop.

including a 2”ZCS103
overlap at the joint. (Fig. 25) use ahacksaw or tin
snips
to trim thepipe as needed.
Zero
Clearance
SleeveFirestop
5. Install first the&innerthen the outer straight pipe
12/6/99end
djtdown, to the point of the elsection(s), trimmed
bow. Drill 3 holes through each joint and fasten withsheet metal screws.

sheet metal screws. Slide the trim collar up against
the wall plate to cover the screws. (Fig. 27)
10. For both MHSC and ST215
DuraVent Systems: Installmeasure thru wallthe vent terminal. (Fig. 28) Apply high temperature
12/6/99 djt
sealant one inch from the ends of the inner and outercollars. Guide the inner and outer vent termination
collars into the adjacent pipes. Double check thatthe vent pipes overlap the collars by 2”. Fasten thetermination to the wall with the screws provided, andcaulk the joint with weatherproof sealant.
11. For MHSC only: Install Charcoal Gray Pipe Rings(#7FSDRG) or Polished Brass Pipe Rings (#7FSDRP) at pipe joints, if desired.

Trim Collar
WallSleeveX

Wall Plate

ST216

Fig. 27 Install the horizontal pipe and wall plate parts.
ST214aFig. 25 Determine the vertical pipe length.

6. Seal and install the elbow using 3 sheet metalscrews at each joint. ST214a
measure vertical vent
7. Measure, and cut if needed,
12/6/99thedjtappropriate length ofpipe section needed to make the connection throughthe wall. Include a 2” overlap; i.e. from the elbow
to the outside wall face, about 2” or the distancerequired if installing a second 90° elbow. (Fig. 26)
8. Slip the wall plate and trim collar over the interior endof the horizontal pipe and install into the wall sleeve.
Seal the joint inside the wall plate if needed to keep
cold air from being drawn into the home.
9. Seal the ends and connect the horizontal pipe to theelbow. Fasten the wall plate to the pipe with three
18

Seal Both Terminal Ends

ST216
install pipe thru wall
12/6/99 djt

Caulk Plate Joint with
Weatherproof Sealant

ST217

Fig. 28 Install the vent terminal.

ST217
install wall terminal
12/6/99 djt

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Vent Termination Below Grade

Recessed Wall

Install Snorkel Kit #7FSDVSKS when it is not possible
to meet the required vent termination clearances of 12”(305 mm) above grade level. The snorkel kit will allow
installation depth of down to 7” (178 mm) below gradelevel. The seven inches is measured from the center ofthe horizontal vent pipe as it penetrates the wall. If theventing system is installed below grade, a window
well must be installed with adequate and proper
drainage. (Fig. 29)
Wall Screws
and Anchors
SnorkelTermination
Cap

Firestop
Finishing Collar

Sheet Metal
Screws andBracketWall Screws andAnchor
Waterproof Seal
Around Pipe7” PipeWall Plate

Waterproof Seal
Around PIpe

ST219

Fig. 30 Use extension brackets to mount snorkel against
recessed wall.

Firestop

Vertical (Through the Roof)
ST219
Vent
Assembly4”

snorkel detail

Note that all vertically12/6/99
terminated
djt installations must
include the restrictor plate included with the stove.
Refer to Page 9, Figure 8.

Drain
Window Well

Make certain the vent system conforms to all otherrequirements for vertical termination as specified onPage 8.
This installation will require you to first determine theroof pitch and use the appropriate vent components.
Refer to Pages 9 and 11, Figures 8 and 11.
ST218aFig. 29 Snorkel kit installation.

NOTE: Be sure to maintain sidewall clearances andST218
vent run restrictions. Refer toinstall
Figures5, 6, 7, and 8.
snorkel
12/6/99
djt
1. Establish the vent hole through the wall.
2. Remove soil to a depth of approximately 16”(400mm) below the base of the snorkel. Install awindow well (not supplied). Refill the hole with 12”(305mm) of coarse gravel and maintain a clearanceof at least 4” (102 mm) below the snorkel. (Fig. 33)
3. Install the vent system as described on Pages 15-18.
4. Be sure to make a watertight joint around the ventpipe joint at the inside and outside wall joints.
5. Apply high temperature sealant around the innerand outer snorkel collars. Join the pipes and fasten
the snorkel termination to the wall with the screws
provided.
6. Level the soil to maintain a 4” clearance below thesnorkel.
If the foundation is recessed, use extension brackets(not supplied) to fasten the lower portion of the snorkel. Fasten the brackets to the wall first, and thenfasten to the snorkel with self-tapping #8 x 1/2” sheet
metal screws. Extend the vent pipes out as far as the
protruding wall face. (Fig. 30)
30004968

1. Locate the final position of the stove, observing all
clearances for both the vent and the stove.
2. Plumb to the center of the inner (4”) flue collar fromthe ceiling above, and mark that location.
3. Cut the opening:
		
MHSC System: 9C\,” x 9C\,” (240 x 240mm)
		
DuraVent System: 10” x 10” (254 x 254mm)
4. Plumb any additional opening through the roof orother construction that may be needed. In all cases,
the opening must provide a minimum of 1” (25 mm)clearance to the vent pipe.
5. Place the stove in its final position.
6. Install firestop(s) #7DVFS and Attic Insulation Shield#7DVAIS as needed. (Fig. 31) If there is a room
above ceiling level, a firestop must be installed on
both the bottom and top sides of the ceiling joists.
If an attic is above ceiling level, an attic insulation
shield must be installed.
7. Install the appropriate roof support and flashing,making certain that the upper flange of the flashingbase is below the shingles. (Fig. 32)
8. Install appropriate pipe sections until the vent run
reaches above the flashing. The enlarged ends ofthe vent sections always face downward.

19

Stardance® Direct Vent/Natural Vent Gas Heater#7DVAIS
Attic Insulation
ShieldSelkirk Direct-Temp Metalbestos Direct
Vent System
Installation Instructions#7DVFS
Firestop inUpper Floor

Use Four
8dNails#7DVFS
Firestop in
Ceiling

ST222

Fig. 31 Install firestops and attic insulation shield.
Use three #5 sheet
metal screws at
each joint

ST222
vent thru ceiling
12/99

Sealant

Storm Collar

Upperedge offlangegoes underuppershinglesFlashing#7DVSKV(A, B, or F)
RoofSupport

ST221

Fig. 32 Roof support and flashing.

9. Install the storm collarST221
and seal around the joints.
vent thru roof
(Fig. 32)
12/99 to achieve the proper
10. Add additional vent lengths
overall height.
11. Apply cement to the inner and outer termination collars and install the terminal cap.

20

1. Determine whether the length of pipe fits the appliance outlet by attempting to engage the parts. If theparts engage smoothly, proceed to Step 2. If obstructions, interference or loose fit is noted, contact
the appliance manufacturer or Selkirk Metalbestos
with the dimensions of the appliance outlet.
2. Slide the length of pipe over the appliance outlet aminimum of 1Z\x” and screw to the appliance outlet
collar using a minimum of two (2) #8 x 1/4” sheet
metal screws.
Appliance Adapter (AAV)
The appliance adapter (AAV) adapts DIRECT-TEMP to
most direct vent appliances incorporating outlet collars
configured to receive most common 4” (ID) 6B\,” (OD) or
5” (ID) by 8” (OD) “Twist Lock” Style, direct vent systems.
The adapter incorporates two (2) indentations on theouter wall of the inlet end, which are designed to “Twist
Lock” into place upon attachment to the applianceoutlet. Align the adapter indentations with the entry
slots of the appliance outlet and slide together. Turn theadapter clockwise approximately one-quarter turn tolock in place. The outlet end of the adapter is standard
DIRECT-TEMP construction.
Framing Dimension Table 1
Model DT Ceiling Support (CS) Cathedral Ceiling Wall Thimble
DiameterFirestop (FS)Support CCS)
(WT)
4”8Z\v” x 8Z\v”
10B\,” x 10B\,”
8Z\v” x 8Z\v”
5”
10Z\,” x 10Z\,”
14Z\x” x 14Z\x”
10Z\,” x 10Z\,”

Use of Sealant
It is not required to apply or use sealant on the inner
liner of DIRECT-TEMP. For outer wall joint sealing
considerations, follow appliance manufacturer recommendations.
Joint Connection:
The pipe and elbows are assembled by inserting theoutlet (male) end of a length of pipe or elbow into the inlet (female) end of an adjacent length of pipe or elbow.
Make sure the outlet end is fully seated within the inlet
end of the adjoining section and the gasket, located on
the inner liner of the inlet section is fully enclosed by the
inner liner of the outlet of the adjoining section. Pushin the Lock Tab such that it becomes seated within the
inward groove of the adjoining section. This locks thejoint in place. (Fig. 33)

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
GasketOutlet End

Inlet End

Lock TabTo Termination

To Appliance

ST922

Fig. 33 Joint connection.

Vent Termination (VC)

Horizontal Termination (HC)343ELKIRK SEAL

Trim Plate (TP)(Required if Wall
Thimble is not used)
Pipe Length

Storm Collar (SC)Wall Thimble (WT)
(Optional)

90° Elbow(EL90)

Roof Flashing (AF)

Pipe Length
Ceiling Support(CS)

Appliance Adapter(AAV)

Trim Plate (TP)Pipe Length

Horizontal Venting

Pipe Length

Vertical Venting
ST925

Appliance Adapter(AAV)

Fig. 34 Selkirk Venting Components

ST924

30004968

21

Stardance® Direct Vent/Natural Vent Gas Heater
Supporting DIRECT-TEMP: Vertical Support
Vertical installations can be supported by two methods:
Ceiling Support (CS) (used in flat ceiling installation)
comes with a support plate and a support collar. Installit by screwing the support plate to the top of the properly framed ceiling joist opening, using screws provided.
A round trim plate (TP) is attached to the ceiling, using
screws, to provide a finished appearance once installed. (Fig. 35)

Ceiling Support
Plate

ST923

Ceiling Support
Collar

If any offsets are necessary in the vertical system, an
Offset Support (OS) should be installed directly above
the upper elbow of the offset. Install by attaching theoffset support band to the pipe with two #8 x 1/4” sheet
metal screws (minimum ) and secure the offset support
straps to surrounding structure. (Fig. 37)
Nail to top offraming

Offset Support
Strap

Offset Support
Collar

ST927

Trim Plate

Fig. 37 Offset support.

Supporting DIRECT-TEMP: Horizontal Support

Fig. 35 Ceiling support.

The Cathedral Ceiling Support (CCS) may be used in
pitched or flat ceiling installations and comes with asupport collar and a decorative
two part square trim
34
plate. Install by inserting the3ELKIRK
support box down throughthe framed joist opening (endwith SUPPORT
round hole first) in
VERTICAL
the ceiling using tin snips, cut
the corners of the open
end of the box such that the sides can be folded downover the top of the joist framing members. Nail thefolded sides to the top of the framing. (Fig. 36)

Two Part Square
Trim Plate
Support Box

Support Box Collar
ST926

Fig. 36 Support box.

A two-part square trim plate is provided to give a finished look once installed. Simply fit the two halves of
the trim plate around34
the cathedral ceiling support box
hanging below the ceiling(overlapping
if necessary)
3ELKIRK3UPPORT "OX
and screw them to the ceiling. Both the ceiling supportand cathedral ceiling support can support a maximumof 40’ (12 m) of pipe.

22

Offsets:

Horizontal runs of Direct-Temp should be supported
every 4’ (122 cm) of pipe.
This can be done with the use+4
of plumbers strapping ortheoffset SUPPORT
support.
SLKRK OFFSET


Adjustable Length (AJ)
An Adjustable Length is available to accommodate
installations where non-standard lengths are necessary.
The adjustable length telescopes down over a standard
length of pipe and provides an extension range of 3Z\x”(89 mm) to 10Z\x” (267 mm). Install by sliding the inlet
end of the adjustable length over the outlet end of astandard length of pipe. After positioning the adjustable
length appropriately, secure it to the standard lengthwith two (2) #8 x1/4” sheet metal screws (provided).
Seal the area between both the top and bottom of theadjustable length outer wall and the outer wall of thestandard length with an approved silicone sealant.
Fire Stopping
DIRECT-TEMP must be firestopped wherever it passes
through floors, ceiling or walls. The only location wherea firestop is not required is at the roof level. Both vertical support components with trim plates provide forfirestopping. The wall thimble also acts as a firestop.
at other locations, a firestop spacer (FS) should be installed. In the attic the firestop should be placed on topof the joist framing to prevent debris from falling into thejoist framing. (Fig. 38)

Horizontal Installation
1. Determine the appliance location. Refer to the appliance manufacturer’s installation instructions for clearance to combustible requirements, termination options,
number of elbows, maximum length, etc. Then position the appliance and plan vent routing accordingly.
30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Firestop (FS)Placed on Top
of Framed
Opening

Maintain at Least
Minimum Clearance to
Combustibles, Wire andInsulation

Attic Framing(No floor)

NOTE: As a general rule, the wall thimble is optional in
the U.S. However, there may be some manufacturersthat require it. Contact the appliance manufacturer for
information if uncertain. When installed in Canada, awall thimble is required on all installations in which
the vent passes through a combustible wall.
5. If required, install the outside half of the wall thimble(WT) through the opening and screw or nail in place. (Fig.
40) Seal around the perimeter of the thimble face plate on
the exterior wall using an RTV silicone sealant to provide
protection from possible rain infiltration. (Fig. 40)
Wall Thimble
ShieldST928

Fig. 38 Firestop spacer.

Consider locating theappliance in a place where there
34
will be no interference with wall studs, electrical wir3ELKIRKFIRESTOPing, conduit, plumbing
pipe orother obstructions. Thetermination should belocated at least 12” (305 mm)(Fig. 39) above grade, remain above the snow line ingeographical areas that accumulate snow and be awayfrom traffic areas such as walkways if it is less than 7’(2.1 m) high. Refer to Pages 11, 12, Figures 11, 12 formore detail.
Snorkel Termination

Wall
ThimbleShieldWall
ThimbleFace
Plate

Seal with RTV
Silicone Sealant
on Exterior side
here (aroundperimeter)

Wall Thimble
Face Plate

ST930

Fig. 40 Wall thimble.

Window Well

Maintain 2”(51 mm)Clearance
Below Snorkel

12” (305 mm) Minimum
Clearance Above Grade Level to
Air Intake
Grade Level
Sloped Away
From Building

Adequate
Drainage as per
Local Codes

ST929

Fig. 39 Below grade installation.

2. Assemble the pipe (and elbow if using) and attach itto the appliance. Plan for a level to 1/4” per foot rise (6mm per 305 mm) (from inlet
to outlet) in the horizontal
34
system if not specified by3LKRK
the appliance
SNORKEL manufacturer.
Horizontal runs should be supported every 4’ (122 cm).

3. Push the appliance near the desired location. Determine the centerpoint of the penetration by locating thecenterline of the outlet of the pipe with respect to the wall.
4. Frame an opening to the dimension specified in the
Framing Dimension Table 1. Ensure the centerline ofthe pipe lines up with the center of the prepared opening unless otherwise specified by the appliance manufacturer.
30004968

NOTE: The wall thimble accommodates wall thicknesses of 4Z\x” (114 mm) to 7Z\x” (191 mm). If a larger range
is needed due to a thicker wall, it is permissible to field
fabricate a metal sleeve extension and attach it to theshields.
34
6. Install the horizontal termination
to theexterior wall
3ELKIRK WALL
THIMBLE
using four (4) all purpose screws through the holes
located at each corner ofthe termination. Make surethe arrow (embossed on the front of the termination)is pointing up. (Fig. 41) If the house has vinyl siding,a Vinyl Siding Standoff (VS) must be installed prior to
installing the horizontal termination. Refer to the appliance manufacturer to determine if one is recommended. Attach the vinyl siding standoff to the exterior sideof the wall (making sure it is level and centered withrespect to the opening) with screws (provided) at eachcorner of the standoff. Attach the horizontal termination
to the standoff. (Fig. 42)
If the wall is brick or concrete, and contains no combustible material, a 7” (178 mm) round penetration
hole is adequate. The wall thimble is not required. The
perforated straps of the horizontal termination provide
a method of attachment. These can either be threaded
through the opening or wall thimble (if used) andscrewed to the pipe or removed with a pair of tin snips
if not used. Use proper masonry fasteners to attach thehorizontal termination to the wall.
23

Stardance® Direct Vent/Natural Vent Gas Heater
Horizontal Termination

Vertical Termination

Storm Collar
Approved Silicone
Sealant HereFlashing

Offset Support
Collar
ST931

Fig. 41 Horizontal termination.

Firestop
SpacerVinyl Siding Standoff

34
3ELKIRK (ORIZ TERMINATIONHorizontal Termination
ST932

Ceiling
Support
Plate

Ceiling Support Collar

Fig. 42 Vinyl siding standoff and horizontal termination.

7. If a wall thimble is used, push the pipe (which isconnected to the appliance) carefully through the wall
ST932
thimble until the DIRECT-TEMP
pipe becomes fully
Selkirk standoff
engaged with the horizontal
termination. If no thimble is
6/07
used, place the Trim
Plate (TP) on the DIRECT-TEMP
pipe. Carefully push the DIRECT-TEMP pipe throughthe wall until fully engaged with the horizontal termination. Secure the trim plate to the wall.
NOTE: If a vertical rise is necessary on the exterior sideof the building, a 14” (356 mm) and 36” (914 mm) Snorkel Termination (ST) is available. Follow the installation
procedures for horizontal terminations. If the snorkel
termination is to be located below grade, a window wellis recommended with adequate and proper drainage
as per local codes. Leave 2” (51 mm) clearance below snorkel to prevent water from entering the snorkel
termination. Do not enclose the snorkel within a wall orother type of enclosure and do not back fill. Ensurethat grade level slopes away from the building. (Fig. 39)

Vertical Installation (Fig. 43)
1. Determine the location of the appliance. Choose
a location which provides adequate clearance fromobstacles such as electrical wiring, conduit, framing
members, plumbing pipe, etc.
24

Trim Plate

ST933

Fig. 43 Typical vertical venting configuration.

2. After positioning the appliance, determine where thevent pipe will pass through the ceiling. This can be doneby using a plum bob or a small weight attached to a34string. Hold theplum bob from the ceiling moving it until
VERTICALofVENTING
it lines up with3ELKIRK
the centerline
the outlet of the appliance. Mark theposition on the ceiling.
NOTE: Frame openings to the dimensions specified
in the framing table for the cathedral ceiling support
box (CCS), the ceiling support (SC) and wherever thefirestop spacer (FS) is being used.
3. Cut and frame the appropriate sized square holethrough the ceiling. Repeat the process for other ceiling
penetrations as necessary.
4. Determine and mark the roof penetration in thesame manner.
5. Cut a hole in the roof at this point large enough tosatisfy all clearance-to-combustible requirements as
specified by the appliance manufacturer’s installation
instructions.
30004968

Stardance® Direct Vent/Natural Vent Gas Heater
6. Install the ceiling support cathedral ceiling support
box assembly, as appropriate.
7. Determine the distance from the appliance outlet toa point just above [approximately 12” (305 mm) to 24”(610 mm)] either the cathedral ceiling support box or
the ceiling support plate and assemble lengths of pipe
to satisfy this distance. Do not attach assembly to appliance.
8. Loosely position the support collar around the assembled lengths (flared end down).
9. From above, lower the assembled pipe sections
down through the cathedral ceiling box or ceiling support plate and attach it to the appliance adapter. The
support collar should then be adjusted so that when
the assembled lengths of pipe are attached to the appliance, it rests on the bottom of the cathedral ceilingsupport box on top of the ceiling support plate.
10. Tighten the tabs of the collar. Secure the support collar by inserting three (3) #8 x 1/4” sheet metalscrews through the support collar and the outer wall of
the pipe.
NOTE: If the cathedral ceiling support box assembly is
being used, it may be necessary to temporarily connect
the assembled pipe to the appliance. Determine andmark the location of where the support collar will be attached to the pipe. Disconnect and remove assembled
pipe. Attach the support collar per Step 10 (where
marked) and reinstall assembly. This is due to limited
space within the cathedral ceiling support box. Install
any required offset supports.
11. Add lengths of pipe and firestop as necessary
until assembly extends to a point above the roof which
complies with local code requirements for minimum termination height and with the appliance manufacturer’s
installation instructions. (Fig. 44)
		Minimum
Roof Pitch
HeightFlat to 7/12	
1’0”Over 7/12 to 8/12	
1’6”Over 8/12 to 8/12	2’0”
Over 9/12 to 10/12	2’6”
Over 10/12 to 11/12	
3’3”Over 11/12 to 12/12	
4’0”Over 12/12 to 14/12	
5’0”Over 14/12 to 16/12	
6’0”Over 16/12 to 18/12	
7’0”Over 18/12 to 20/12	
7’6”Over 20/12 to 21/12	
8’0”

Minimum Height
Above Roof

Fig. 44 Minimum Height Above Roof Requirements

30004968

ST934
minimum height
6/07

NOTE: Whenever DIRECT-TEMP penetrates through aceiling, a floor or a wall, it must be firestopped.
12. Using a level, make sure the system is perfectly
vertical.
13. Slide the flashing, suitable for the roof pitch, downover the pipe protruding through the roof. Recheckorientation and use a silicone sealant around and under
the perimeter of the flashing where it is in contact withthe roof. Secure the flashing with roofing nails. Finish
roofing around the pipe, covering the sides and upperares of the flashing base with roofing material. However, be sure the lower unnailed portion of the basecovers the roofing material.
14. Position the storm collar around the pipe and slide
down until it is in contact with the flashing. Secure thestorm collar by inserting the two (2) tabs into the raisedslots and fold tabs back. Seal the area between thestorm collar and the vent pipe with a silicone sealant toprevent rain infiltration.
15. Install the vertical termination (VC) by inserting it
down into the top most section of pipe until it is fully
seated. Depress lock tab to secure the cap to the pipe.
NOTE: In high wind areas, it is recommended to screw
termination to the pipe with two (2) #8 x 1/4” sheet
metal screws. The screws should be approximately 3/4”
from the bottom of the vertical termination’s galvanizedcollar.

Venting System Assembly - Natural Vent
General Information
The Stardance Heater is shipped from the factory as a
Direct Vent Heater. It may be converted to a Natural
Vent heater by installing the Vermont Castings Model
Z31B00 FSDHAG Draft Hood Adapter.
The Stardance Heater is approved for installation asa Natural Vent. MHSC Direct Vent pipe could be useddirectly after the Draft Hood Adapter up to the ceiling,
then B-vent pipe must be used. Do not mix types of Bvent pipe; use components from one maker or the other.
Follow the vent component maker’s instructions exactly.
The heater will also accept standard or enamelled 7”(178mm) diameter pipe, around the Type B venting, fordecorative purposes only. (Fig. 45)
NOTE: The restrictor plate supplied with the stoveis not used for Natural Vent applications.
The Stardance stove, when installed as a Natural ventheater, includes a vent safety switch. (Page 41, Figure81) Operating the stove when it is not connected to aproperly installed and maintained venting system, or
tampering with or disconnecting the vent safety switch,
can result in carbon monoxide (CO) poisoning and possible death.

25Stardance® Direct Vent/Natural Vent Gas Heater
For U.S. installations: The venting system must conform with local codes and/or the current National Fuel
Gas Code, ANSI Z22.1.
For Canadian installations: The venting system must
conform to the current CSA B149.1 installation code.

Install the Vent Pipe
Apply a bead of sealant around bottom end of inner
starter pipe (found in bag with logset) and attach tostove. Apply a bead of sealant around top of inner
starter pipe and install the Z31B00 FSDHAG Draft Hoodaccording to Draft Hood instructions. (Fig. 45)
Attach the first section of venting to the draft hood. Depending on the length of the individual venting sections
and the lengths of the decorative pipe (if installed), you
may need to slip the decorative pipe over the venting
sections before attaching upper sections to lower ones.
The sections of decorative pipe should be oriented with
their seams (if any) toward the wall; sections usually
do not need to be fastened at each joint, other thanslip sections. If the layout includes a slip section, thisshould be the last section of pipe visible in the room, at
the ceiling. Complete the venting according to the ventmaker’s instructions.

MHSC Direct Vent
System may be
used after Draft
Hood up to theceiling

Decorative7” Pipe4” B-vent
Pipe
Draft Hood
Adapter

ST358

Fig. 45 Decorative 7” pipe may be fitted around the B-ventpipe.

Install the Log Set
CAUTION: Before installation, inspect ember bed
burner for damage. Do not use ember bed if damaged
or cracked. NOTE: Small, shallow surface cracks are
acceptable.
1. Remove the logs from their packaging and inspect
each piece for damage. DO NOT INSTALL DAMAGED LOGS.

ST358
Decorative
pipe around b-vent
4/26/00 djt

Rear Log

Figure 46
2. Install the rear log by mating
the notch on the bottom of
the log with the raised notchon the back left side of theember bed. (Fig. 47) Ensure
the cutout in the right side ofthe log is sitting around thepilot assembly and pilot is
not obstructed. (Fig. 46)

LG493

26

,G
2EAR LOG


30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Figure 47

Raised Notch

Pilot Assembly

Raised Notch
Pin

LG497

3. Install the left log bymating the hole on thebottom of the log withthe pin in the ember
bed. (Fig. 48) Position
the log over air hole inember bed.
4. Install the right log bymating the notch on thebottom of the log withthe raised notch on theember bed. (Fig. 48)
Position the log over air
hole in ember bed.

Figure 48

Left Log,'
3$$64 EMBER BED
Right Log

Rear Log

Figure 49

LG494

Top Log,'
LEFTRIGHT LOGS

Left Log

Right Log

5. Install top log bymating hole on bottom of log with locating pin on top rightside of rear log. (Fig.
49) Position log so
it is angled down toward the area where
the front two logs
meet.

LG495

Ember Bed

30004968,'
3$$64 LOGS COMPLETE


27

Stardance® Direct Vent/Natural Vent Gas Heater
Connect the Gas Supply Line
Check the Rating Plate attached by a steel cable to thefirebox, to confirm that you have the appropriate firebox
for the type of fuel to be used. The Stardance may be
converted from one gas to another using the appropriate Fuel Conversion Kit listed on Page 46.

CAUTION
This appliance should only be connectedby a qualified gas technician. Test to
confirm manifold pressures as specified
below.
The Stardance Heater and its individual shutoff
valve must be disconnected from the gas supply
piping during any pressure testing of that systemat test pressures in excess of 1/2 psig (3.5 kPa).
The Stardance Heater must be isolated from thegas supply piping system by closing its individual manual shutoff valve during any pressure
testing of the gas supply piping system at test
pressure equal to or less than 1/2 psig.
There must be a gas shutoff between the stove
and the supply.
In order to connect Natural Gas, use a fitting with
3/8” NPT nipple on the valve side and 1/2” natural
gas supply line with an input of 28,000 BTUs at a
manifold pressure of 3.5” and minimum inlet supply for adjustment of 5.5” w.c.
In order to connect Propane, use a fitting with
3/8” NPT nipple on the valve side and 1/2” propane gas supply line with an input of 28,000 BTUs
at a manifold pressure of 10.0” and minimum inlet
supply for adjustment of 11.0” w.c.
In the U.S.; Gas connection should be made in accordance with current National Fuel Gas Code, ANSI
Z223.1/NFPA 54. Since some municipalities haveadditional local codes, be sure to consult your local
authority.
In Canada; consult the local authority and CSA-B149.1
installation code.

Conversion instructions are provided with each kit andbeginning on Page 37 in this manual.
THIS APPLIANCE SHOULD BE CONNECTED TO
THE GAS SUPPLY ONLY BY A QUALIFIED GASSERVICE TECHNICIAN.
THERE MUST BE A GAS SHUT-OFF BETWEENTHE STOVE AND THE SUPPLY.
In order to connect Natural Gas, use a fitting with 3/8”
NPT nipple on the valve side and 1/2” natural gas supply line with an input of 28,000 BTUs at a manifold pressure of 3.5” and minimum inlet supply for adjustment of5.5” w.c.
In order to connect Propane, use a fitting with 3/8”
NPT nipple on the valve side and 1/2” propane gas
supply line with an input of 28,000 BTUs at a manifoldpressure of 10.0” and minimum inlet supply for adjustment of 11.0” w.c.

Install ON/OFF Switch
The switch assembly parts are found in the parts bag.
1. Attach switch assembly to left rear side of stove
shroud (when facing shroud) using two screws andexisting holes in shroud. (Fig. 50)
2. Run wires down back of stove, under bottom of rearshroud to valve.
3. Attach wires to valve terminals. (Fig. 51)
SwitchAssembly

Existing Holes

ScrewsST315

Fig. 50 Attach switch assembly to rear shroud.
Valve

SIt Valve
TPTH

Always check for gas leaks with a mild
soap and water solution. Do not use an
open flame for leak testing.

Page 46 for correct conversion kit.

Thermopile

TP

Light the pilot according to the directions on Page 31,
before going to the next step.

TH

Burner Information

28

O
PIL T

The appliance must only use the gas specified on therating plate, unless converted using a Vermont Castings
Fuel Conversion Kit. To convert from Natural Gas to LP
use Kit #20012735 or 20012904. To convert from LP to
Natural Gas use Kit #20012903 or 20012905. Refer to

ON/OFF Switch orMillivolt Thermostat

FP1622
ST315
Fig. 51 Install wiring to switch before attachconnectingswitch
to valve. assy
1/31/00 djt

FP1622
SIT valve w/switch

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Thermostat Connection (optional)
Use only a thermostat rated for 500 millivolts.
Check the table below for the appropriate gauge thermostat wire to use for the length of lead required in yourinstallation.
Thermostat
Wire / Gauge
Maximum Run
18	20 feet
16	20 - 40 feet14
up to 60 feet
1. Install the wall thermostat in the desired location andrun the wires to the stove location. Terminate theseleads with 1/4” female connectors.
2. Connect the thermostat wires to the valve. (Fig. 51)

Install the Front Plate
Hold the front plate by the window bars and lift it into
position, engaging the two steel tabs on the top corners
behind the adjacent bosses in the side plates. (Fig. 53)
Then seat the Front against the sides so the tabs at thebottom lip engage with the notches in the stove legs.
When properly installed, the bottom of the Front Platecannot be pulled away from the sides without also liftingit.
Engage steel tabs
gehind the castiron bosses

Receiver Installation - SDDVTCS Series
Once the blower is installed to the back of the SDDVTCS Series stove, install the receiver.
1. Slide receiver into igniter bracket as shown in Figure52.
2. Attach igniter bracket with receiver to valve with #1032 x 1/4 screws supplied.
3. Connect receiver wiring to valve as shown on Page
43, Figure 91.
4. Plug igniter wire from burner into the back of theigniter bracket.
Receiver installation complete.

Control Door

Bottom tabs engage
notch in the leg.

ST474

Fig. 53 Install the front plate.

ST474 stove.
This completes assembly of the StardanceStardance
Front
10/3/00

ReceiverValve
ST1121

IgniterBracketFig. 52 Install receiver.

ST1121
receiver install

30004968

29

Stardance® Direct Vent/Natural Vent Gas Heater

Operation

 7!2.).'

Pilot and Burner Inspection$/ ./4 4/5#( ',!33
5.4), #//,%$
.%6%2 !,,/7 #(),$2%.
4/ 4/5#( ',!33

The Stardance is operated with the front plate in placewith the doors open or closed. To open the front doors,pull forward to separate the magnetic catch.
CAUTION: DO NOT TOUCH DOORS WHEN
HOT!

Your First Fire
Read these instructions carefully and familiarize yourself with the burner controls. Locate the pilot assembly,
Figure 54. Follow the lighting instructions on Page 31
exactly.
During the first fire, it is not unusual to smell some odor
associated with new logs, paint and metal being heated.
Odors should dissipate within an hour or so, however,you can open a window to provide fresh air to alleviate
the condition.

Each time you light your heater check that the pilot
flame and burner flame patterns are as shown in Figure
56. If flame patterns are incorrect, turn the heater off.
Contact your dealer or a qualified gas technician for assistance. Do not operate the heater until the pilot flame
is correct.
Follow regular maintenance procedures as describedon Page 41.

Flame & Temperature Adjustment
For stoves equipped with HI/LO valves, flame adjustment is accomplished by rotating the HI/LO adjustment
knob located near the center of the gas control valve.
(Fig. 55)

Turncounterclockwise
to increase
flame heightHI(/4 ',!33 7),,#!53% "52.3

LO

Turn clockwise
to decrease
flame heightFig. 55 Flame adjustment knob for SIT valve.

Flame Characteristics
FP390

FLAME ADJUSTMENT
It is important to periodically
performKNOB
a visual check11/21/96of the pilot and the burner flames. Compare them to
Figure 56. If any of the flames appear abnormal, call aservice person.

ST935aFig. 54 Pilot assembly location.

ST935
SDDVT
pilot location
6/07

CO105dFig. 56 Correct pilot and burner flame patterns.

LG496

30

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Lighting and Operating Instructions
FOR YOUR SAFETY READ BEFORE LIGHTINGWARNING:If you do not follow these instructions exactly, a fire or explosion
may result causing property damage, personal injury or loss of life.
A. This heater has a pilot which must be lit manually. When lighting the pilot follow these instructions exactly.
B. BEFORE LIGHTING smell all around theheater area for gas. Be sure to smell next to
the floor because some gas is heavier than air
and will settle on the floor.
WHAT TO DO IF YOU SMELL GAS• Do not try to light any fireplace• Do not touch any electric switch• Do not use any phone in your building• Immediately call your gas supplier from aneighbor’s phone.

Follow the gas supplier’s instructions.

• If you cannot reach your gas supplier, callthe Fire Department
C. Use only your hand to push in or turn the gas
control knob. Never use tools. If the knob will notpush in or turn by hand, do not try to repair it, call aqualified service technician. Applying force or any
attempted repair may result in a fire or explosion.
D. Do not use this fireplace if any part has been underwater. Immediately call a qualified service technician to inspect the heater and to replace any part ofthe control system and any gas control which has
been under water.

Lighting Instructions
1. STOP! Read the safety information above.
2. Turn off all electrical power to the fireplace.
3. Turn the On/Off switch to “OFF” position, set
the remote to OFF or set thermostat to lowest
level.
4. Open control access panel.
5. Push in gas control knob slightly and turn clockwise
to “OFF”.

10. Push the control knob all the way in and hold.
Immediately light the pilot by repeatedly depressing the piezo spark ignitor until a flame appears.
Continue to hold the control knob in for about one(1) minute after the pilot is lit. Release knob and it
will pop back up. Pilot should remain lit. If it goesout, repeat steps 5 through 8.

3/8" - 1/2"

OFF

ON

OFF

ON

OFF

1 2

P
OFF ilot

PI

LO

T

PILOT

3 4 5

SIT NOVA•If knob does not pop up when released, stop
andimmediately
call your service technician or
6. Remove glass door before lighting pilot. (Seegassupplier.
FP1068Glass Frame Removal section).
•If after several tries, the pilot will not stay lit,
7. Wait five (5) minutes
to clear out any gas. ThenLighting instructions
FP1067
Pilotsturn
thegas control knob to “OFF” and call yourlighting
instruction
smell for gas, including near the floor. If you
knobs
servicetechnician
or gas supplier.
smell gas, STOP!3/9/01
Follow“B” in the safety infordjt
11.
Replaceglass
door.
mation above. If you do not smell gas, go to the
12. Turn gas control knob to “ON” position.
next step.
13. Turn the On/Off switch to “ON” position or set
8. Visibly locate pilot by the main burner.
thermostat to desired setting.
9. Turn knob on gas control counterclockwise
14.
Turn on all electrical power to the fireplace.
to “PILOT”.

To Turn Off Gas To Heater
1. Turn the On/Off switch to Off position or set
the thermostat to lowest setting.
2. Turn off all electric power to the fireplace if
service is to be performed.
30004968

3. Open control access panel.
4. Push in gas control knob slightly and turn clockwise
to “OFF”. Do not force.
5. Close control access panel.
31

Stardance® Direct Vent/Natural Vent Gas Heater
Troubleshooting the Gas Control System (SDDVT Series)
SIT NOVA 820 MILLIVOLT VALVENOTE: Before trouble shooting the gas control system, be sure external gas shut off is in the “On” position.

Symptom

Possible Causes

Corrective Action

1. Spark ignitor will not light

A. Defective or misaligned electrodeat pilot

Using a match, light pilot. If pilot lights, turn off pilot andpush the red button again. If pilot will not light - checkgap at electrode and pilot-should be 1/8” to have astrong spark.

B. Defective ignitor (Push Button)

2. Pilot will not stay lit after
carefully following lighting
instructions

3. Pilot burning, no gas tomain burner

4. Frequent pilot outage
problem

32

With the control knob in the pilot position, push thecontrol knob all the way and hold. Check for spark atelectrode and pilot. If no spark to pilot, and electrodewire is properly connected, replace the battery in theignitor module and try again. Refer to Maintenance
Section. If the problem still exists, replace the ignitor
module box.

A. Defective pilot generator (thermocouple), remote wall switch

Check pilot flame. Must impinge on thermocouple/thermopile. NOTE: This pilot burner assembly utilizes botha thermocouple and a thermopile. The thermocouple
operates the main valve operation (On and Off). Clean
and or adjust pilot for maximum flame impingement on
thermopile and thermocouple.

B. Defective automatic valve

Turn valve knob to “Pilot”. Maintain flow to pilot; millivolt
meter should read greater than 10mV. If the reading
is okay and the pilot does not stay on, replace the gas
valve. NOTE: An interrupter block (not supplied) must
be used to conduct this test.

A. Wall switch or wires defective

Check wall switch and wires for proper connections.
Jumper wire across terminals at wall switch, if burnercomes on, replace defective wall switch.. If okay,
jumper wires across wall switch wires at valve, if burnercomes on, wires are faulty or connections are bad.

B. Thermopile may not be generating sufficient millivoltage

1. Be sure wire connections form thermopile at gas
valve terminals are tight and thermopile is fully
inserted into pilot bracket.
2. One of the wall switch wires may be grounded. Remove wall switch wires form valve terminals if pilot
now stays lit, trace wall switch wiring for ground.
May be grounded to fireplace or gas supply.
3. Check thermopile with millivolt meter. Take readingat thermopile terminals of gas valve. Should read
250-300 millivolts (minimum 150) while holding
valve knob depressed in pilot position and wall
switch “Off”. Replace faulty thermopile if reading is
below specified minimum.

C. Plugged burner orifice

Check burner orifices for debris and remove.

D. Defective automatic valve operator

Turn valve knob to “On”, place wall switch to “On”
millivolt meter should read greater than 150mV. If thereading is okay and the burner does not come on,
replace the gas valve.

A. Pilot flame may be too low or
blowing (high) causing the pilot
safety to drop out

Clean and/or adjust pilot flame for maximum flame
impingement on thermopile and thermocouple.

B. Possible blockage of the ventterminal

Check the vent terminal for blockage (recycling the fluegases).

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Instructions for RCSITEASDDVTCS Series
CAUTION: The RCSITEA is only certified for use on
vented heater rated equipment.
This remote control system provides a safe, reliable
and user-friendly remote control for millivolt valve gas
appliances, blower speed and flame height adjustment.
The system can be manually or thermostatically turnedon and off with the transmitter.
Carefully inspect the contents for shipping damage. If
any parts are missing or damaged, immediately contact
your dealer. Do not attempt to install any part of the kit
unless all parts are in good condition. Refer to instructions provided with the kit for complete installation
instructions.
WARNING: Make sure 120V AC fan and SIT valve arecorrect. If not wired correctly, damage to receiver could
result. Make sure the wires do not contact the appliances any place other than at the terminals. Exposure totemperatures higher than 250°F (105°C) may cause thereceiver to malfunction and cause possible fire hazard.

Remote Transmitter
Install Batteries
The remote transmitter uses three(3) “AAA” batteries.

Battery
Door
Tab

1. Press down the battery door tab
and pull out to remove the battery door. (Fig. 57)
2. Install the batteries as indicatedon transmitter.
3. Close the battery door by snapping in place.
4. When three (3) batteries are
Fig. 57 Batinstalled, the transmitter will
initialize for 10 seconds and then tery door tab.
is ready for use.
ST1088
5. The batteries should be replaced atleast once
every
RCSITE
batterytabsix (6) months or when the low battery indicator isdisplayed.
Setting Privacy (DIP) Switch on Receiver and Transmitter
The remote receiver and transmitter privacy (DIP)
switches are preset at the factory. In the event of activation or interference from other nearby transmissions,reset the code using the following procedure:
1. Slide the code switches on the transmitter and receiver to choice of ON or OFF position. Switches #1,#2, #3 and #4 are preset to “ON” for both the transmitter and receiver. (Fig. 58)

30004968

2. The switches on the transmitter and receiver mustmatch in order for the system to work.
3. To check, press either the ON or OFF button on thetransmitter and the receiver indicator light will blink.
If not, repeat Step 2.
4. The system is now ready to operate.
NOTE: Refer to optional 6 Hour Shutdown.
WARNING: Do not use two (2) or more remotecontrol systems in the same area with thesame dip switch settings, they will communicate with each other. This may cause theappliances to malfunction.
Dip Switch(Default)

ON

ON

DIP

DIP

ReceiverTransmitter

ST1089Fig. 58 The switches on the transmitter and receiver mustmatch.
ST1089Reset Button

RCSITE dip switches

The reset button can be used to reset the transmitter
if transmitter is not working properly. The reset button
is located behind the battery door cover in the lower
left corner of battery compartment. Using a paper clip,
press the reset button and the transmitter will reset andinitialize for 10 seconds before it can be used.

Operation
Transmitter
GeneralThe RCSITEA Remote Control
has two (2) operating modes:
Manual and Thermostatic. The
control system can be set totemperature ranges between 45°F
and 90°F. The blower speed andflame height can be adjusted ineither the manual or thermostatic
mode.
The transmitter will operate theremote receiver from 1 foot to a
maximum of 30 feet. The distanceis reduce when batteries are low
or when the receiver is inside a
metal enclosure.

ON
FAN

AUTO
FLAME

OFF

AMBIENT

Fig. 59 RCSITEA
remote transmitter.

ST109033
RCSITE remoteStardance® Direct Vent/Natural Vent Gas Heater
Initial Startup
Figure 60
1. After initial power up or°Fwhen RESET button ispressed, the transmitter isreset. The reset button is
located behind the battery
door of transmitter.
2. During system reset,
FP2142all features of the LCD
Fig. 60 Typical ResetDISPLAY will be visible.
Display
FP2142After one second, the LCD
initial start up
will be initialized. A typical reset display
is shown in
Figure 60. Note the temperature scale is degree F.
3. Press ON button to select between °C and °F display. It will exit setting mode automatically after 10
seconds if no key is pressed. The transmitter will
send an OFF signal after reset.
4. After reset, the transmitter is operating in manualmode. The room temperature is shown.

Manual Mode
Figure 61
1. Press the ON button once
to turn on the appliance°Fwith max flame height.
2. Press the OFF button to
decrease flame height.
The first two (2) presses
will decrease flame heightFP2143
to lower level. The thirdpress will turn off the fireFig. 61 Manual mode.
place.
FP2143
3. If the OFF button is held for moremanual
than threemode(3)seconds, the fireplace will be shut12/08
off.

Thermostatic Mode
Figure 62
1. Press the AUTO/FLAME
button to enter the ther°F
mostatic mode.
2. In thermostatic mode,press the ON / ▲ button°For OFF / ▼ button to set
SETthe desired set temperature.
FP2144
3. Once the setting is comFig. 62 Thermostatic
pleted, the transmittermode.
FP2144will automatically turn on
thermostat modethe fireplace when the room temperature
is below
12/08
the set temperature and turn off the fireplace when
the room temperature is above the set temperature
within 1 degree.

34

4. There will be a slight delay in the response of theunit (on/off) to a temperature. Room temperature ismonitored every three (3) minutes.
5. Press AUTO/FLAME button to exit the thermostaticmode. The transmitter will be in the manual off modeand the fireplace will be shut off.

Flame Height Setting for Thermostatic Mode
Figure 63
1. Hold AUTO/FLAME button
for five (5) seconds andone number and flame
icon will appear in LCD
screen.
2. Use the ON / ▲ or OFF / ▼button to set the desired
flame height to 1 (min.) 2
FP2147(medium) or 3 (max.).
Fig. 63 Flame height
3. If there is no input withinsetting.
three (3) seconds, theFP2147new setting will be transflame height setting
mitted to the receiver. This setting
12/08only affects automode operation.
4. The default setting for transmitter is 2 (medium).

3-Speed Blower Control
Figure 64
1. Press FAN button once
to enter blower speed°F
setup mode at low speed
initially and one of thethree blade icons will display darkened on LCD
display.
2. Continue to press FAN
FP2145button to set the blower
Fig. 64 3 speed blower
speed you desire.
FP2145
3. If there is no input within control.
3 speed fan
three (3) seconds, the
new setting will be transmitted12/08
to receiver. If the fireplace is on, the blower speed will take effect right away;
if the fireplace is off, the receiver will remember thissetting and blower is still off.
4. If you continue to press FAN button to the position thatall blades are gone, the FAN icon will disappear andturn the blower off.

Blower On Delay Time and OFF Delay Time Setting (Default 5 ON / 8 OFF)
Figure 65
1. Hold FAN button for five (5) seconds and two (2) numbers will appear in the LCD screen. The upper one is
ON Delay Time and the bottom is OFF Delay Time inminutes.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
2. Use the ON / ▲ button
to set the desired On
Delay Time from 0 to 15
minutes.
3. Use the OFF / ▼ button
to set the desired Off
Delay Time from 0 to 15
minutes.
FP2146
4. If there is no input within
3 seconds, the new set- Fig. 65 Blower time delayting will be transmitted to display.
FP2146
receiver.
blower delay timer
5. The default settings for both transmitterand receiver
12/08
are 5 minutes for ON delay time and 8 minutes for OFF
delay time.

Low Battery Detection
Figure 66
1. Battery voltage is checked
once a minute. When the°Fbattery voltage drops to acertain level, the low-battery icon will display on
LCD, and the transmitter will turn off the appliance. The transmitter
FP2150will not function anymore
Fig. 66 Low battery
until fresh batteries are
display.
installed.
FP2150low battery display
2. When the batteries are
12/08
low, the LCD displays a low battery
indicator. The low
battery indicator will be displayed in any mode.
3. The transmitter will not operate with low batteries.
Change the batteries before the batteries are too weakfor normal operation. Turn the unit OFF before replacing batteries.

Child-Proof Protection
Figure 67
1. Press and hold the ON
and OFF buttons simul°F
taneously for three (3)seconds to enter child
proof mode.
2. The transmitter will not
send a signal again until
the childproof mode isFP2151
deactivated by pressing
Fig. 67 Child protection
the ON and OFF buttons
display.
FP2151
simultaneously for three
no child display(3) seconds to exit child
12/08 disappears fromproof mode. The Childproof indicator
LCD.

30004968

Transmitter Thermal Shutdown
Figure 68
1. If transmitter measuresa room temperature
exceeding 99° F, the LCD
will display "HI" and thetransmitter will turn off theappliance.
2. Transmitter will not function until the room temFP2152
perature has dropped
below 99° F. If transmitter Fig. 68 Thermal shutdown
FP2152
measures a room tem- display.
thermal shutdown display
perature less than 40° F,
12/08
the LCD will display "LO" and NO
SIGNAL will be sent
to turn on the appliance.

ReceiverSlide Switch
1. ON position: The main burner will ignite and blower will
come on when blower on delay time is reached andfan speed has been enabled, the flame height is max;otherwise just burner will ignite until the slide switch isplaced in the OFF or RS position to turn burner off.
2. RS position: The system will only operate if the remotereceiver receives a signal from the transmitter.
3. OFF position: The system is off. If fan speed has beenenabled, blower will continue to operate until OFF delay
time expires. The slide switch should be placed in the
OFF position if you will be away for an extended periodof time. If the remote receiver is mounted out of reachof children, the OFF position also functions as a safety
device by both turning the system off and rendering
the receiver inoperable.
Optional 6 Hour Shutdown
1. The receiver comes preset from the factory with a 6hour shutdown from its last ON or flame lower operation. This is done to prevent the appliance from continuing to operate if unattended.
2. You may disable this feature if you wish. To disable,change the receiver privacy (DIP) switch #1 ONLY to
the OFF position. Make sure the transmitter privacy(DIP) switches are set the same as the receiver. Follow
the instructions on how to set the privacy (DIP) switch
setting.
3. By disabling this feature, your appliance may continue
operating unattended.

35

Stardance® Direct Vent/Natural Vent Gas Heater
Testing Remote Control System
1. Light the gas appliance following the lighting instructions on Page xx. Confirm the pilot light is on; it must
be in operation for the remote control to operate themain gas valve and blower. Appliance control knob
must be in the ON position, and ON/OFF switch
must be in OFF position.
2. Slide the 3 position button on the remote receiverto the ON position and the main gas flame should
ignite.
3. Slide the button to OFF and the main gas flame
should extinguish, but the pilot light will remain lit.
4. Slide the button to RS (the center position). Press
the ON button on transmitter to turn the system ON.
The main gas flame should ignite and blower shouldcome on after the On delay time is reached and fan
speed you desire is selected.
5. Press the OFF button on transmitter to turn the system to OFF. The flame should extinguish (the pilot
light will remain lit) and blower should be off after the
Off delay time is you set is reached.

Troubleshooting
Symptom
1. Battery icon on LCD on transmitter.
2. LCD display is blank.
3. LCD display shows “funny” display.
4. Appliance does not come on.

5. Receiver cannot receive signal.
6. Blower is not on after the stove isturned on.

Causes
1. Low battery.

1. Wiring/Electrical connections.

2. Privacy (DIP) switch setting ontransmitter does not match receiver.
3. Transmitter measure temperature exceeding 99°F andshows “HI” on LCD.
4. Distance between the transmitter and receiver is morethan 30 feet.
1. Receiver is installed in an enclosure.
1. Blower setting is off.
2. Blower delay setting is set too
high.

36

Action1. Replace batteries. Change the batteries every 6 months.
2. Check battery installation or replacebatteries.
3. Press reset button at the back of thetransmitter.
1. Slide the switch to ON, if appliancecomes on, wiring is not the cause.
2. If appliance, does not come on,check wiring connections.
1. Make sure the transmitter and receiver have the same DIP switch
settings.
1. Move transmitter to a cooler place
and wait until temperature drops below 99°.
1. Make sure the operating distance isless than 30 feet.
1. Make sure the receiver is not located inside too tight of an enclosure.
1. Press FAN key to select desired fan
speed.
2. Press and hold Fan key to set desired ON/OFF delays. This is donein minutes.

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Fuel Conversion Instructions()()

nal key-way ofthe screw (Fig.
71), rotate it
Figure 70
Figurecounterclock71
wise until it
is free andextract it.
5. Check that the,/screw is clean
and if necessary remove,/dirt.
6. Flip the screw.
(Fig. 72)
Figure 72
7. Using the Al#/
REMOVE SCREW
len wrench as
Figure 73
shown in Figure#/73, rotate the!LLEN WRENCH
screw clockwise
and tighten until,/
snug.
WARNING: Do
not overtighten
the screw. Recommended togrip the wrench,/by the shortside.
8. Verify that if theconversion is from NG to LP, thescrew must be reassembled#/with the red o-ring vis#/
ible. (Fig. 74)!LLEN WRENCH

Fig. 69 Attach the gas line to the left side of the valve.

Conversion Precautions
Before proceeding, turn control knob on valve to OFF
ST226band turn gas supply OFF.
Turn
attachgasOFFline any electricity that
may be going to the appliance.
6/07 djt

Conversion Procedure
1. Remove stove front. Lift stove front up and thenswing bottom out and away to disengage from thestove body. (Page 41, Fig. 84)
2. Swing open the swiveling latches at the top left andright corners of the glass frame. (Page 42, Fig. 85)
3. Pull the top edge of the glass and frame assemblyaway from the firebox face. Place the assembly outof the way on a flat, padded surface such as a counter protected by a towel.
4. Remove the logset from the firebox.
Valve Conversion
SDDVT Series Models
1. Turn control knob to the OFF position, and shut off
the gas supply to the valve.
2. Allow the valve to cool to room temperature.
3. Remove the black protection cap by hand. (Fig. 70)
4. Insert a 5/32” or 4 mm Allen wrench into the hexago30004968

TURN SCREW

Figure 74

LP Configuration

Natural Gas
Configuration()

Gas Supply Inlet()

ST226aMain Gas
Line

()

()

WARNING! This conversion kit shall be installed
by a qualified service agency in accordance withthe manufacturer’s instructions and all applicable
codes and requirements of the authority having
jurisdiction. If the information in these instructions is not followed exactly, a fire, explosion
or production of carbon monoxide may result
causing property damage, personal injury or lossof life. The qualified service agency is responsible for the proper installation of this kit. The
installation is not proper and complete until theoperation of the converted appliance is checked
as specified in the manufacturer’s instructions
supplied with the kit.
CAUTION: The gas supply shall be shut off prior
to disconnecting the electrical power, before proceeding with the conversion.

,/,/

Red O-ring Visible
Red O-ring NOT Visible

CO141

9. Replace the black protection cap.
WARNING: Check that also the pilot andmain burner injectors are appropriate forthe gas
type.
CO141

O-ring configuration
6/07

37

Stardance® Direct Vent/Natural Vent Gas Heater
SDDVTCS Series Models
1. Using the TORX T20 bit remove and discard thethree (3) pressure regulator mounting screws fromthe old pressure regulator assembly. (Fig. 75)

2. Replace pilot orifice.
3. Remove pilot hood by lifting up. (Fig. 77) Do notremove snap ring to remove pilot hood. NOTE: It is
not necessary to remove the pilot tube for conversion.
Index Tab

Allen Wrench

Snap Ring
CO106aFig. 77 Remove pilot orifice.

ST1093

4. Remove pilot orifice with Allen wrench. (Fig. 78)
5. Install the conversion orifice.
CO106a
6. Reinstall pilot hood. Be
sure to align hood with index
DV360/580
tab.
Gas Conversion
Pilot2
1/28/00 djt
Pilot HoodFig. 75 Remove mounting screws from old pressure regulator assembly. Replacestep motor with new conversion step
ST1093
motor.

install new step motor

2. Insure the rubber gasket (D) is properly positioned
and install the new step motor (E) pressure regulator
assembly to the valve using the new screws suppliedwith the kit. Tighten the screws securely. (Ref. torque= 25 in/lb) (Fig. 75)
3. Install the identification label (F) supplied with the
stepper motor to the valve body where it can easily
be seen. (Fig. 75)
4. Make step motor and mV valve electrical connections.
5. Regulator conversion complete.
6. Test for Leaks
Pilot Orifice Conversion
1. Locate pilot. (Fig. 76)

Pilot
BracketCO105aFig. 78 Remove pilot hood.

Burner Orifice Conversion
1. Remove three (3) 3/8” nuts on bottom side of burnerpan. (Fig. 79)
2. Carefully remove ember bed by tilting the right side
up and lifting out towardCO105a
the right side of the unit.
(Fig. 79)
gas conversion

Pilot
Remove Nut
1/28/00 djt

ST935

Fig. 76 Pilot assembly location.

ST935
SDDVT
pilot location
6/07
38

Bottom View

Remove Nuts

ST918

Fig. 79 Remove three (3) nuts securing ember bed in place.

34
REMOVE NUTS

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Orifice
BracketVenturi Bracket

Orifice

Orifice
BracketAir Shutter

CO142

Pem Studs

ST919

Fig. 80 Tilt ember bed slightly to correctly place on venturi
and air shutter.

34
3. Remove injector orifice fromleft burner bracket witha 1/2” wrench. Use a backwrenchto prevent
TILTup
EMBER
BED
damage to the manifold.
(Fig. 81)
4. Install conversion orifice. (Refer to Table 2)
5. The air shutter is factory set according to table on
Page 7 and should not need adjustment. The air
shutter opening may be verified by measuring as
shown in Figure 82.

Fig. 82 The air shutter setting is 1/2” (13 mm) from the orificebracket to the edge of the air shutter.

#/
All Models
AIR SHUTTER MEAS
1. Replace burner making sure venturi on bottom ofember bed aligns with orifice and is seated properly
on air shutter assembly. (Fig. 80) Make sure burneris slid into place at a slight angle and opposite to
how it was removed. When burner is slid into place,the three (3) pem studs should slide down throughclearance holes into the bottom of the control panel.
2. Thread and tighten 3/8” nuts back onto pem studs
on underneath side of control panel, reversing Step
1 shown in Figure 79.
3. Reinstall logs as per instructions on Page 25.
4. Place conversion label supplied in the kit on the rating plate.
5. Replace glass and stove front.
6. Restore gas to system and relight appliance according to Lighting Instructions on Page 30.
7. Leak check the system using a gas leak detector
solution.
8. Relight the main burner in both the “HI” and “LO” positions to verify proper burner ignition and operation.
Conversion is complete.

CO145

Fig. 81 Use two wrenches to avoid damage to manifold.

Table 2. Injector Orifice Size Matrix
Conversion to LP						Input (BTU/h)
#O
Model
Kit #
Orifice
Part #
Minimum		Maximum
BACKUP
WRENCHSDDVT	20012735
		20,000				

#53 / .0595”	20007347

		28,000

SDDVTCS	20300126
20,000Conversion to Natural Gas
						Input (BTU/h)
Model
Kit #
Orifice
Part #
Minimum		Maximum
SDDVT	20012903
		20,000				#38 / .101”	20009310

SDDVTCS	20300127
30004968

		28,000

20,00039

Stardance® Direct Vent/Natural Vent Gas Heater

MaintenanceYour Stardance Gas Heater will provide years of service
with minimal upkeep. The following procedures will help
ensure that your stove continues to function properly.

Annual System Inspection
Have the entire heater and venting system inspectedannually by a qualified gas technician. Replace any
worn or broken parts.

Cleaning the GlassWARNING: Allow the glass to cool completely before attempting to clean.

 7!2.).'(/4 ',!33 7),,#!53% "52.3

Logset and Burner /Cleaning and Inspection
Cleanliness is critical to the proper function of theheater. The logset and burner must all be kept free of
dust and unobstructed by debris. Inspect these areas
before each use and clean as necessary.
1. Turn the burner OFF and let the heater cool completely before cleaning.
2. Lift the Stove Front up and then swing the bottom
out to disengage it from the heater shell. (Fig. 83)
3. Carefully remove the glass and frame assembly andplace it out of the way on a flat, padded surface suchas a counter protected by a towel.
4. Carefully inspect the Logs for damage. Contact yourlocal dealer if any damage is evident. DO NOT OPERATE THE HEATER WITH DAMAGED LOGS.
5. Use a soft bristled brush to sweep dust or debris
from the Logs, Pilot and Burner. Use care as the logs
are fragile and susceptible to damage. DO NOT USE
A VACUUM TO CLEAN THE LOGS OR BURNER.
6. Replace the glass panel and frame assembly.
7. Replace the Stove Front.

Care of Cast Iron$/ ./4 4/5#( ',!33
5.4), #//,%$
.%6%2 !,,/7 #(),$2%.
4/ 4/5#( ',!33

It will be necessary to clean the glass periodically. During start-up, condensation, which is normal, forms on
the inside of the glass and causes lint, dust and otherairborne particles to cling to the glass surface. Also
initial paint curing may deposit a slight film on the glass.
It is therefore recommended that the glass be cleaned
two or three times with a non-ammonia householdcleaner and warm water (we recommend gas fireplace
glass cleaner). After that the glass should be cleaned
two or three times during each heating season depending on the circumstances present.
Clean glass after first two weeks of operation.

Glass Replacement
Replace glass only with MHSC approved parts. Refer toPage 44 for Replacement Parts. Refer to Figures 83 &84 for removal of the damaged glass frame.

An occasional dusting with a dry rag will help keep the
painted surfaces looking new. Use high-temperature
stove paints, available through your local dealer, totouch-up areas as needed. Clean areas to be painted
with a wire brush and be sure to cover the logs, burnerand valve assembly, glass and frame assembly. Apply
the paint sparingly; two light coats of paint will give better results than a single heavy coat.
Clean porcelain enamel surfaces with a soft, damp
cloth. Do not use abrasive cleaning agents. If necessary, use only a cleaning agent formulated especiallyfor use on porcelain enamel surfaces.

CAUTION
TURN THE PILOT OFF BEFORE PAINTING. ALLOW THE HEATER TO COOL COMPLETELY BEFORE PAINTING.

40

ST474aFig. 83 Remove the stove front.

ST474
Stardance
30004968
Remove Front
10/3/00

Stardance® Direct Vent/Natural Vent Gas Heater
Inspect the Vent System Annually

ST208

Fig. 84 Release the latches to release the glass frame.

Gasket Replacement
The Stardance Gas Heater uses a ‘tadpole’ type gasket
to seal between the glass panel and the frame. In time,
this gasket can become brittle and compressed andshould be replaced. New gasket is available from yourdealer.
Shut off the gas supply and allow the stove to cool.
Wear safety goggles and a dust mask.
1. Remove the Front, Glass Frame and Glass Panel.
(Figs. 83 & 84) Remove the old gasket. Use arazor blade
to separate the glass and gasket fromST208
the frame, and to clean the glass of any remaining
glass swivel latch
cement or bits of gasket. Use a cold chisel if neces12/99
sary.
2. Determine the correct length of gasket by laying it
out around the edge of the glass. Allow an extra 1- 2” (25-50mm). Mark the spot to be cut. Use a utility
knife.
3. Starting on a long edge, remove about 6” of the protective paper strip and apply the flat adhesive faceof the gasket around the outside-facing edge of thepanel. Continue around the panel, applying a bout 6”
at a time and being careful to not stretch the material. Do not overlap the gasket ends. (Fig. 85)
4. Apply a thin bead of high temperature silicone rubber
sealant along the inside corner of the glass frame, allaround the perimeter. Place the flat gasketed side of
the glass panel back into the steel frame. Pinch therounded inside-facing gasket material to bulk it up.
5. Replace the glass frame and front panel as previously described.

Have the vent system inspected annually by a qualified
technician. Shut off the main gas supply before inspecting the system. Both the inner exhaust pipe and the outer combustion supply pipe must be checked to confirm
that they are unblocked and in good condition.

Check the Gas Flame Regularly
To ensure that the stove is operating properly, check theflames periodically to confirm that they match Figure 86.
The flames will be blue during the first 15-20 minutes ofoperation, and will gradually turn to yellow after that.
Do not use your stove if the flame pattern differs fromthat shown here. Contact your Vermont Castings dealer
or a qualified technician for help.

Figure 86

Stove Disassembly
If there is ever a need to remove the firebox assem,'
bly from the stove shell,
support the firebox with solid
LOG FLAMES
stands about 6” (1523$$64mm) tallunder the left and rightouter edges of the firebox base. Do not set the firebox
assembly directly on the floor; this can damage thecontrol valve and/or the gas lines from the valve to thefirebox.
Before removing the firebox from the shell, disconnect
the on/off switch wires from the valve. If the assembly
includes the optional fan, disconnect the fan rheostat.
If the installation includes a wall thermostat, disconnect
the thermostat leads from valve.
Disconnection and reconnection to the gas line should
only be done by a qualified gas service technician.

ST179

Fig. 85 Wrap the gasket material around the outside iedge ofthe glass.

30004968

ST179
glass gasket detail
11/99

Upon reinstallation, the vent system must be sealed to
the firebox as shown in the installation section, Page
14. Also be sure the logs are placed in the firebox correctly, as shown on Page 25, Figures 46-49.
41

Stardance® Direct Vent/Natural Vent Gas Heater
Wiring Diagrams - SDDVT
ON

OFF

Thermopile

Black
TP/TH

K

Black

TH

ChassisGroundST124b
Thermostat

BL

Thermopile

Black

GRN

Thermostat(Optional)(Optional)
Optional Thermostat
WiringTP

St124bon/off/switch
wiring
1/11/00 djt

K

BLK

FAN JUNCTION BOX
Millivolt
Gas Valve

Strain Relief

Black

TH

ST124cON / OFF
RheostatFig. 87 On/Off switch and optional thermostat circuit.

NOTE: IF ANY OF THE ORIGINAL WIRE, AS
SUPPLIED WITH THE APPLIANCE, MUST BE
REPLACED, IT MUST
BE REPLACED WITH TYPE
St124cSF-2, 200°C WIRE OR
ITS EQUIVALENT.
Thermostat

Snapstat

LK

WHT
BLK

B

wiringDrafthood
Adapterdjt
1/11/00
Remote Wall Switch,
Harness

GRN

Remote Control
or ON/OFF Rocker Switch

RHEOSTAT / SNAPSTATBOX

Chassis Ground

Optional Blower Kit Wiring Diagram

TH
TP

MOTOR

Gas
Valve

TH
TP

ST943

BLK

Fig. 88 Draft hood adapter wiring.

ST943
FSDHAG Wiring
6/07

ST153

Optional Blower Kit
Schematic Diagram
BLK

Draft Hood
Adapter for
SDDVT andSDDVTCS

BLK

WHT
BL

Millivolt
Gas Valve

TP

TP/TH

FAN

POWER
CORD

On/Off Switch
Wiring

ST153
rdv connections diag.
10/99 BLK

WHT

GRN

WHT

BLK

SNAPSTAT

ON/OFFRHEOSTAT

ST234

Fig. 89 Stardance fan circuit.

42

ST236
FK26 wiring diagram
12/99

30004968

Stardance® Direct Vent/Natural Vent Gas Heater
Wiring Diagrams - SDDVTCS

Black
120V AC AdapterBlackmV Valve

TH
TP /TH

Receiver120V AC Plug

FemaleMale

SIT HI / LO
Valve

120V AC
Blower

ST1091aFig. 90 SIT Hi/Lo blower schematic.

ST1090120V AC Plug for Receiver
SIT valve wiring

SIT mV Valve

Receiver
Tag
Tag

Tag: to blower

Tag:
to 120V AC

Hi/Lo Regulator

Blower

120V AC Plug for Blower

ST1092bFig. 91 SIT Hi/Lo blower wiring.

30004968

ST1092b
SIT valve schematic

43

Stardance® Direct Vent/Natural Vent Gas Heater
2
1

6

5

1a

4

1c
1d
3

1b

8
14

7

11

12

15
10

9
16

13

17
18
19a,b

27a,b

28a,b

34
22 23

21

ON

24

20

N

FA

TO E
AU AM
FL

31

F

OF

32

ON
RS

29

OF

F

36

33

25

35

26
38

37

48

39

NT

E
EM

C
47

MHSC reserves the right to make changes in design, materials, specifications, prices and discontinue colors and products at any time, without
notice.

Stardance Direct Vent/Natural Vent Gas Heater
Models:4968
Stardance
SDDVT/TCS parts
8/09

SDDVT Series: SDDVTCB, SDDVTEB, SDDVTBS, SDDVTBD, SDDVTBMSDDVTCS Series: SDDVTCSCB, SDDVTCSEB, SDDVTCSBS, SDDVTCSBD, SDDVTCSBM

44

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Stardance Direct Vent/Natural Vent Gas Heater

SDDVT Series: SDDVTCB, SDDVTEB, SDDVTBS, SDDVTBD, SDDVTBMSDDVTCS Series: SDDVTCSCB, SDDVTCSEB, SDDVTCSBS, SDDVTCSBD, SDDVTCSBM
Ref. Description
SDDVT/SDDVTCS
1. Log Set - Complete	20012551
1a. Log Rear 	20012546
1b. Log Right 	20012548
1c. Log Left 	20012547
1d. Log Top	20012915
	2. Ember Bed Assembly	20012492
3. TopRefer to Enamel Parts Chart
4. Front, Operable Door
Refer to Enamel Parts Chart
5. Door Right
Refer to Enamel Parts Chart
6. Door Left
Refer to Enamel Parts Chart
7. Left End
Refer to Enamel Parts Chart
8. Right End
Refer to Enamel Parts Chart
9. Door, Control
1301087
10. Glass Frame Assembly
30000127
11. Glass1601691
12. Gasket, Glass - Med. Knit
1203702
13. Nut, Hex Jam 3/8-16 TOPLK-Z
1203290
14. Pawl Assy, Ash Door
5004025
15. Front Steel Handle/Shaft - NI/VER
30002717
16. Restrictor Plate 	20013026
17. Fan Blower (SDDVTCS Series Only)
30005069
18. Valve Nova SIT820.852 RN	20012218
18a. Valve SIT MV HI/LO 0.820.652 - Nat. (SDDVTCS Series only)
37D011719a. Stepper Motor - SIT820 - Nat. (SDDVTCS Series only)
50D009919b. Stepper Motor - SIT820 - LP (SDDVTCS Series only)
50D0100			20a. Pilot Assembly 3Way N/DV RN 0.199.706
10002264	20b. Pilot Assembly 3Way N/DV RP 0.199.703
10002265	21. Pilot Top Convertible
10002266
	22. Thermocouple 24”53373						7531137
	23. Electrode Ignitor w/Cable SIT24
10001297	24. Thermopile 18” RS
51827						7533113
	25. Nut Electrode SIT #0.974.144
57886
	26. Tubing Pilot w/Fittings 1/8 x 24”
10001296
	27a. Pilot Orifice #62 - NG Top Convertible
37D0022	27b. Pilot Orifice #35 - LP Top Convertible
37D0023
	28a. Orifice Hood #53 (.0595”) LP	20007347
	28b. Orifice Hood #38 (0.101”) Nat.	20009310
	29. Ignitor Piezo w/Nut SIT
05795830. Bracket Piezo Ignitor/Control (not shown) (SDDVTCS Series only)	20300111
31. Manifold Assembly	20012553
32. Air Shutter Assembly	20012517
33. Trim ON/OFF Switch
30000874
34. Remote Kit (Hi/Lo, Blower) (SDDVTCS Series only)
RCSITEA
30004968

45

Stardance® Direct Vent/Natural Vent Gas Heater

Stardance Direct Vent/Natural Vent Gas Heater

SDDVT Series: SDDVTCB, SDDVTEB, SDDVTBS, SDDVTBD, SDDVTBMSDDVTCS Series: SDDVTCSCB, SDDVTCSEB, SDDVTCSBS, SDDVTCSBD, SDDVTCSBM

Ref. Description
35.
36.
37.
38.
39.
40.
42.
43.
44.
45.
46.
47.
48.
49.

SDDVT/SDDVTCS

Sensor 1450 CMG-8184-0032 (for use with FSDHAG only)
10002013
Wiring Harness
10002582
Gasket, Base Pan	20002282
Gasket HE Door
1203687
Gasket Cement
1206122
Handle Package, Ceramic w/Screw (not shown)
0004345
Switch Bracket (not shown)
53821
Starter Pipe (not shown)
30000245
Rear Shroud (not shown)	20003802
1/4” Fiberglass Gasket (not shown)1203560*Magnet, Door (not shown)
30004112
Right Burner Support Assembly	20012512
Tie Bracket Assembly	20012514
Rear Shroud Assy. (SDDVTCS Series Only) (not shown)	20300122*Use common super glue or silicone to attach magnets.

Fuel Conversion Kits
Conversion Kit, NG to LP - SDDVT Series
Conversion Kit, NG to LP - SDDVTC Series
Conversion Kit, LP to NG - SDDVT Series
Conversion Kit, LP to NG - SDDVTC Series

46

Kit #20012735
Kit #20300126
Kit #20012903
Kit #20300127

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

Stardance Direct Vent/Natural Vent Gas Heater

SDDVT Series: SDDVTCB, SDDVTEB, SDDVTBS, SDDVTBD, SDDVTBMSDDVTCS Series: SDDVTCSCB, SDDVTCSEB, SDDVTCSBS, SDDVTCSBD, SDDVTCSBM

Shell Enamel Part Numbers
		
Color
Top
Classic Black
30001276
Biscuit		
30003305
Bordeaux
30001283
Brown Majolica
30004897
Ebony Black
30001304

Left End
30001280
30003300
30001287
30004895
30001308

Right End
30001279
30003301
30001286
30004896
30001307

Front OP
30001496
30003302	
30001261
30004899
30001270

Left Door* Right Door* Left Door** Right Door**
30001139
30001138
30004082	
30004081
30003304
30003303
30004090
30004089
30001263
30001262	
30004084
30004083
n/a
n/a
30004900
30004901
30001272	 30001271
30004086
30004085* These doors have a front handle.
** These doors do not have a handle, they are closed with a magnet.

30004968

47

Stardance® Direct Vent/Natural Vent Gas Heater

Optional Accessories
Fan Kit - STDDVT
FK26 Fan
The FK26 fan helps distribute heated air from within
the firebox out into the room. The fan is controlled by asnapstat that turns power on and off as the firebox temperature rises above and falls below a preset temperature. A rheostat provides for variable fan speeds. Used
with standard millivolt models.
115 Volt / 60Hz / .75 Amps
Maintenance
The fan itself does not require regular maintenance,
however, periodic cleaning of the fan and the surrounding area is required.
Installation
Refer to Page 15 for installation instructions.

Remote Controls - SDDVTThe remote control allows you to turn the heater on or
off from anywhere in the room. Refer to Page 43 for wiring diagrams. These remotes for use with RN/RP model
gas stoves.
Functions Controlled

RCB,RCM,
RCBE,WMTD
RCST,RCSTE,RCT,
WWTD,RCSTEB,RCSITEA, RCSIT
WT
MVWS

48

An optional screen, S30SK, for use with the operable
doors is available to allow the doors to be left in the
open position.

Warming Shelf
Warming shelves add versatility to your stove; they canbe used to keep foods warm at mealtime.
Model		

Specifications

Model

Screen Kit

On/Off Remote
ON/OFF Thermostat Remote	2702	
	2681
	2684
	2704
	2765

Color

Classic Black
Brown Majolica
BiscuitBordeaux
Ebony BlackThe shelf installation is done in three stages. First you
attach the shelf loosely to the stove, leaving the screws
loose enough to allow final adjustments. Then, you position the shelf and adjust the brackets so the shelf fitscorrectly. Finally, you tighten the screws.
Refer to the instructions included with each warming
shelf for complete installation procedures.

Decorative Rings
7” brass or charcoal gray rings are available to add adecorative touch to the exposed stove pipe.
Model

Description

7FSDRG/4
7FSDRP/4

7” Charcoal Gray Rings (4)7” Polished Brass Rings (4)Wall Thermostat
Wall Switch

30004968

Stardance® Direct Vent/Natural Vent Gas Heater

30004968

49

Stardance® Direct Vent/Natural Vent Gas Heater

50

30004968

Stardance®
Direct Vent/Natural Vent Gas Heater
LIMITED LIFETIMEWARRANTY
PRODUCT COVERED BY THIS WARRANTYAll Vermont Castings brand gas stoves, gas inserts, and gas fireplaces installed in the United States ofAmerica or Canada.
LIMITED LIFETIME WARRANTYMHSC warrants that all cast iron parts, the combustion
chamber, ceramic burner, and heat exchanger of every Vermont
Castings gas product will be free of defective material orworkmanship during the period the product is owned by theoriginal owner subject to proof of purchase and the conditions
and limitations listed on this warranty document.
BASIC ONE-YEAR WARRANTYMHSC warrants to the original owner that your new Vermont
Castings Gas Appliance is free from defects in material
or workmanship for a period of one year from the date ofpurchase, subject to the following conditions and limitations.
Labor to replace these parts is covered for one year, reimbursed
per our warranty service fee schedule.
COMPONENT WARRANTY LIMITATATIONSPORCELAIN ENAMEL FINISHED PARTS: MHSC offers nowarranty on chipping of enamel surfaces. Inspect all products
prior to accepting them for any damage to the enamel. The
salt air environment of coastal areas or a high humidity
environment can be corrosive to the porcelain enamel finish.
These conditions can cause rusting of the cast iron beneath theporcelain enamel finish, which will cause the finish to flake off.
Color lot variations with parts and/or accessories can occur andare not covered by warranty.
GLASS: Glass is not warranted for breakage due to misuse or
accident. Glass is not covered for discoloration or stains due toenvironmental issues, or improper cleaning and maintenance.
PLATED PARTS AND ACCESSORIES: Brass, nickel, and goldparts should be cleaned with Lemon oil only. Commercial
cleaners cannot be used. Mortar mix and masonry cleaners
corrode the brass finish. The MHSC will not be responsible
for, nor will it warrant any brass parts which are damaged byexternal chemicals or down draft conditions.
ACCESSORIES: Unless otherwise noted, MHSC supplied
accessories are covered for a period of one year.
GENERAL CONDITIONS AND LIMITATIONS• This Vermont Castings product must be installed or serviced bya qualified installer, preferably NFI or WETT (Canada) certified,
as prescribed by the local jurisdiction. It must be installed andoperated at all times in accordance with the Installation andOperating instructions furnished with the product. Any alteration,
willful abuse, accident, or misuse of the product shall nullify thiswarranty.
• This warranty is non-transferable, and is made to the original
owner, provided that the purchase was made through an
authorized supplier of Vermont Castings branded MHSC
products.
• Parts covered under the Limited Lifetime Warranty will becovered for the lifetime of the appliance up to a maximumof seven (7) years after MHSC discontinues the model. The
maximum amount recoverable under this warranty is limited
to the purchase price of the product and, if MHSC is unable toprovide replacement or repair in an expedient and cost effective
manner, MHSC may discharge all obligations under thiswarranty by refunding the purchase price of the product.
• Any labor and related repair charges relating to the cost andexpenses of replacing or repairing defective components
under the Limited Lifetime Warranty are not covered, except asprovided for under the Basic One-Year Warranty.

30004968•

Any part or component replaced under the provisions of thiswarranty is covered for six months or the remainder of theoriginal warranty, whichever is longest.
• Any installation, labor, construction, transportation, or otherrelated costs/expenses arising from defective part(s), repair,
replacement, or otherwise of same, will not be covered by thiswarranty, nor shall the Company assume responsibility forsame. IN NO EVENT SHALL MHSC BE LIABLE FOR ANY
INCIDENTAL OR CONSEQUENTIAL DAMAGES CAUSED BY
DEFECTS IN THE PRODUCT except as provided by law• SOME STATES DO NOT ALLOW FOR THE EXCLUSION
OR LIMITATIONS OF INCIDENTAL AND CONSEQUENTIAL
DAMAGES OR LIMITATIONS ON HOW LONG AN IMPLIEDWARRANTY LASTS, SO THE ABOVE LIMITATIONS MAY NOTAPPLY TO YOUR CIRCUMSTANCES. THIS WARRANTYGIVES YOU SPECIFIC RIGHTS AND YOU MAY HAVE OTHERRIGHTS WHICH VARY FROM STATE TO STATE.
• All other warranties expressed or implied with respect to the
product, its components and accessories, or any obligations/liabilities on the part of the Company are hereby expressly
excluded.
• The Company neither assumes, nor authorizes any third party
to assume on its behalf, any other liabilities with respect to thesale of this Vermont Castings product• The warranties as outlined within this document do not apply tochimney components or other non MHSC accessories used inconjunction with the installation of this product.
• Damage to the unit while in transit is not covered by thiswarranty but is subject to claim against the common carrier.
Contact the dealer from whom you purchased your fireplace/stove (do not operate the appliance as this might negate theability to process the claim with the carrier).
• The Company will not be responsible for:a) Down drafts or spillage caused by environmental conditions
such as near-by trees, buildings, roof tops, hills, or mountains.
b) Inadequate ventilation or negative air pressure caused bymechanical systems such as furnaces, fans, clothes dryers, etc.
• This warranty is void if:a) The fireplace has been operated in atmospheres contaminatedby chlorine, fluorine, or other damaging chemicals.
b) The fireplace has been subjected to prolonged periods ofdampness or condensationc) Any damages to the fireplace, combustion chamber, heatexchanger or other components due to water, or weather
damage, which is the result of but not limited to, improperchimney/venting installation.
d) Any alteration, willful abuse, accident, or misuse of the producthas occurred.

IF WARRANTY SERVICE IS NEEDED...
Contact your installing Vermont Castings dealer. Make
sure you have your warranty, your sales receipt, the model
number and serial number of your MHSC product. If
you’re the installing dealer is unknown or unable to provide
necessary parts or service, a list of Authorized Vermont
Casting dealers can be located on the internet at www.
vermontcastings.com

51

MHSC
149 Cleveland Drive • Paris, Kentucky 40361
www.mhsc.com