MWCP SERIESPACKAGED AIR
CONDITIONER
R407C

R407H

※optional

R407C/R407H Series [Scroll Type]
ModelPower

MWCP10C

Main circuit (Control circuit)

MWCP18C

MWCP30C

380V/3~/50Hz, 440V/3~/60Hz ( 220V~/50Hz, 220V~/60Hz )Painting color

New light blue (7.5BG7/2) and Black

Dimensions

HxWxD

mm

1725 x 800 x 600

1725 x 1050 x 600

1725 x 1250 x 600★1

Cooling capacity(50/60Hz)kW

8.0/9.5

13.5/15.8

20.6/23.5★2

Cooling water flow rate(Fresh water)(50/60Hz)

L/min

31.7/38.3

53.3/63.3

80.0/95.0Head loss (Cooling water)(50/60Hz)

kPa

Model

2.0/3.0

11.0/15.0

4.0/6.0

ZR36K3E-TFD-522 x1

ZR57KCE-TFD-522 x1

ZR94KCE-TFD-522 x1

Scroll typeType
Compressor

Speed2900/3450(50/60Hz)r/min

Motor power(50/60Hz)kW

2.24 x 1

3.58 x 1

5.97 x 1

Rated current(50/60Hz)A

4.8 x 1/4.9 x 1

7.9 x 1/8.0 x 1

12.9 x 1/12.8 x 1

M02214717004

M02214717005

Direct start

Starting manner
ModelWater
cooling
condenser

Material

Tube

Copper tubes TP2(GB/T 1527)

Shell

20(GB 8163)

Tube plate

Evaporator

Q235B (GB 3274)

No.

1

11

Model

3ROWx14FPIx20THx578mm

3ROWx14FPIx20THx828mm

3ROWx14FPIx20THx1028mm

TypeMaterial

Crossfincoil type
TubeCopper tubes

Fin

Aluminium fins

Model

SYD160L

TypeFan

M02214717006

Water cooled shell & tubeType

SYD200L

SYD200L

Centrifugal fan

Air flow rate

(50/60Hz)m /min

22/27

40/49

50/60

External static press(50/60Hz)

Pa

45/60

80/120170/240

kW

0.55

1.1

1.5

Motor power
Drive

Belt drive

Air filter

Nylon mesh

Refrigerant control

Thermostatic expansion valveTemperature control

Control module,MWP010,SLM2.3

Capacity step%

100-0100-0100-0

Circuit breaker(for comp.& fan motor), Overload protector(for comp.& fan motor), Fusible plug,Protective devices

Reverse phase protector, High pressure switch, Low pressure switch, Comp. protection thermostat, Freeze-up protection
thermostat, The comp. frequent starts and stops protection, Temperature sensor fault protection.

Thermal & sound isorator
Pipingconnection★3
Refrigerant
Lubricant oil

Class 1 flex (NBR/PVC)

Chilled water inlet/outlet

1B(DN25)

1-1/2B(DN40)

1-1/2B(DN40)

Upper drain outlet

3/4B(DN20)

3/4B(DN20)

3/4B(DN20)

Lower drain outlet

3/4B(DN20)

3/4B(DN20)

3/4B(DN20)

Kind
ChargedR407C/R407Hkg

2.4 x 1Kind

3.6 x 1

4.8 x 1

POE (Copeland Ultra22cc)

ChargedL

1.242 x 1

1.952 x 1

2.513 x 1

★3

Machine mass

kg

245

290

360

★3

Operating mass

kg

248

295368★ 1 Cooling capacity is based on the following conditions : Evaporator : Inlet air temp : 27°C d.b.,19.5°C w.b. Cooling capacity does not include fan motor heat.
★ 2 Condenser : Inlet water temp. 38°C.
★ 3 The mass of refrigerant,machine and operating may be changed.

©2017 ShenZhen McQuay

MWCPX SERIESPACKAGED AIR
CONDITIONER for Galley
R407C

R407H

※optional

R407C/R407H Series [Scroll Type]
Model
Power

MWCPX10C

Main circuit (Control circuit)

MWCPX18C

MWCPX30C

380V/3~/50Hz, 440V/3~/60Hz ( 220V~/50Hz, 220V~/60Hz )Painting color

New light blue (7.5BG7/2) and Black

Dimensions

HxWxD

mm

1725 x 800 x 600

1725 x 1050 x 600★1Cooling capacity(50/60Hz)kW

9.9/11.5

16.0/18.9

24.6/28.5★2

Cooling water flow rate(Fresh water)(50/60Hz)

L/min

38.3/44.8

60.0/72.3

90.0/108.3

Head loss (Cooling water)(50/60Hz)

kPa

Model

7.0/10.0

13.0/18.0

4.0/6.0

ZR36K3E-TFD-522 x1

ZR57KCE-TFD-522 x1

ZR94KTE-TFD-522 x1

Scroll typeType
Compressor

Speed2900/3450(50/60Hz)r/min

Motor power(50/60Hz)kW

2.24 x 1

3.58 x 1

5.97 x 1

Rated current(50/60Hz)A

4.8 x 1/4.9 x 1

7.9 x 1/8.0 x 1

12.9 x 1/12.8 x 1

M02214717004

M02214717005

Direct start

Starting manner
Model

Material

Tube

Copper tubes TP2(GB/T 1527)

Shell

20(GB 8163)

Tube plate

Evaporator

Q235B (GB 3274)

No.

1

1

1Model

3ROWx14FPIx20THx578mm

3ROWx14FPIx20THx828mm

3ROWx14FPIx20THx1028mm

Type
Material

Crossfincoil type
Tube

Copper tubes

Fin

Aluminium fins

Model

SYQ200L

TypeFan

M02214717006

Water cooled shell & tube

Type
Water
cooling
condenser

1725 x 1250 x 600

SYQ200L

SYQ200L

Centrifugal fan

Air flow rate

(50/60Hz)m /min10/12

16.7/20

25/30

External static press(50/60Hz)Pa

265/380

325/465

340/495

kW

0.55

0.75

1.1

Motor power
Drive

Belt drive

Air filter

Nylon mesh

Refrigerant control

Thermostatic expansion valve

Temperature control

Control module,MWP010,SLM2.3

Capacity step

%

100-0

100-0

100-0

Circuit breaker(for comp.& fan motor), Overload protector(for comp.& fan motor), Fusible plug,Protective devices

Reverse phase protector, High pressure switch, Low pressure switch, Comp. protection thermostat, Freeze-up protection
thermostat, The comp. frequent starts and stops protection, Temperature sensor fault protection.

Thermal & sound isorator
Pipingconnection★3Refrigerant
Lubricant oil

Class 1 flex (NBR/PVC)

Chilled water inlet/outlet

1B(DN25)

1-1/2B(DN40)

1-1/2B(DN40)

Upper drain outlet

3/4B(DN20)

3/4B(DN20)

3/4B(DN20)

Lower drain outlet

3/4B(DN20)

3/4B(DN20)

3/4B(DN20)

Kind
ChargedR407C/R407Hkg

1.9 x 1Kind

3.6 x 1

6.7 x 1

POE (Copeland Ultra22cc)

ChargedL

1.242 x 1

1.952 x 1

2.513 x 1

★3

Machine masskg

250300360★3

Operating masskg253305368★ 1 Cooling capacity is based on the following conditions : Evaporator : Inlet air temp : 27°C d.b.,19.5°C w.b. Cooling capacity does not include fan motor heat.
★ 2 Condenser : Inlet water temp. 38°C.
★ 3 The mass of refrigerant,machine and operating may be changed.

©2017 ShenZhen McQuay