Jøtul GF3 DVII
AllagashDirect Vent
Gas Heater

Installation
andOperation
Instructions

Welcome to Jøtul...
Congratulations on the purchase of your new
Jøtul GF3 DVII Allagash gas stove.
We at Jøtul are happy you’ve made the decision
to warm your hearth with a Jøtul product. Your
new Allagash incorporates our experience as
the world’s largest manufacturer of solid fuelburning appliances for over 150 years. We’ve
been making fine quality cast iron wood andcoal stoves and fireplaces continuously since1853.
In the Allagash, we’ve combined advanced gas
technology with the warm, traditional elementsof cast iron. With proper care and use, yourJøtul heater will provide you with many years of
safe, dependable, and satisfying service.
The Jøtul GF3 DVII Allagash is a direct-vented
gas heater designed and approved for use in avariety of installation configurations. Pleasetake a few minutes to familiarize yourself withthis manual and the features of your new stove.

Jøtul GF3 DVII Allagash
Direct Vent Gas Heater
Manufactured and Distributed by:
Jøtul A.S.A.
Fredrikstad, Norway
Jøtul North America
Portland, Maine

Test Standards
Warnock Hersey
This appliance complies with
National Safety standards and istested and listed by Intertek
Testing Services of Middleton,
Wisconsin to ANSI Z21.88-1998(NFPA 54) and CSA 2.33-M98 for Canada.

CUSTHIS STOVE IS CONFIGURED TO BURN NATURALGAS ONLY. IF USE WITH PROPANE GAS IS DESIRED,THE BURNER MUST FIRST BE CONVERTED. FOR
YOUR CONVENIENCE, A PROPANE CONVERSIONKIT IS INCLUDED WITH THE STOVE.
THIS PRODUCT MUST BE INSTALLED BY A
LICENSED MASTER OR JOURNEYMAN PLUMBER
OR GAS-FITTER WHEN INSTALLED IN THE
COMMONWEALTH OF MASSACHUSETTS.

SUGGESTED TOOL LIST FOR INSTALLATION
AND SERVICE:• External regulator (for LPG only)• Piping which complies with local code
• Manual shutoff valve• Sediment trap
• Tee Handle Gas Cock - required for Massachusetts• Pipe wrench• Pipe sealant• 10 mm open end wrench• 1/2”, 7/16” open end wrench• Phillips head screwdriver• Flat head screwdriver• 1/4” nut driver• Gloves• Safety glasses• Torx T20 screwdriver• Leak test solution

Table of Contents
Standards............................................3
General Information ........................3
Safety Information ...........................4
Location ............................................... 4
Hearth Requirements...................... 4
Stove Clearances...............................5
Mantel and Trim ...............................5
Venting Requirements ....................6
Vertical Venting ................................6
Horizontal Venting ...........................7
Co-linear Hearthmount .................. 8
Mobile Home Installation .............. 9
Vent Window .................................. 10
Vent Terminal Clearances ........... 11
Fuel Conversion .............................. 12
Gas Connection .............................. 14
Gas Pressures.................................. 14High Altitude Adjustment .......... 15
Air Shutter Settings ...................... 16
Log Set Installation ....................... 16
Blower Installation ........................ 17
Remote Control / Thermostat .... 18
System Check ................................. 19
Operation Instructions ................ 20
Maintenance................................... 20
Illustrated Parts List ............... 22, 23

PLEASE READ THESE INSTRUCTIONS IN THEIR ENTIRETY AND MAKE THEMAVAILABLE TO ANYONE USING OR SERVICING THE APPLIANCE.
KEEP THESE INSTRUCTIONS FOR FUTURE USE.

1Specifications
The Jøtul GF3 DVII Allagash is a Direct Vent wall
furnace and is designed as a sealed combustion, air
circulating gas appliance for residential applications.
The following vent components are approved for use
with the Jøtul GF3 DVII, vented directly to theoutside of the house:• Simpson Dura-Vent 6 5/8" X 4" GS pipe
• Security Direct Vent 6/4 vent pipe
• Amerivent 6/4 vent pipe.

28”
711 mmThe Jøtul GF3 DVII Allagash gas stove is designed
to operate on NATURAL GAS or PROPANE only. It
manufactured and shipped prepared to burn Natural
Gas. For safe and efficient operation the stove isequipped with a millivolt gas control valve with apiezo ignitor. Electrical power is only required when
operating the OPTIONAL forced air blower.

22 3/4”578 mmInput Rates
Top Exit
27 3/4”705 mmNatural Gas
26,000 BTU/hr. maximum input
20,000 BTU/hr. minimum input

Propane26,000 BTU/hr. maximum input
20,000 BTU/hr. minimum input

Minimum Inlet Pressure:
Natural Gas:
Propane:5.0 WC (1.25 kPa)
11.0 WC (2.75 kPa)

Manifold Pressure:
Natural Gas:
Propane:MIN
2.0 WC (.85 kPa)
6.4 WC (1.60 kPa)

Steady State Efficiency: 82%
A.F.U.E.: 73%
Piezo Ignitor / Standing Pilot

Rear Exit
Centerline
24 3/4”629 mm13 1/4”337 mm2

MAX
3.5 WC (.85 kPa)
10.0 WC (2.50 kPa)

Standards
This appliance complies with National Safety standards and is tested and listed by Intertek Testing
Services of Middleton, WI
In addition, the Jøtul GF3 DVII Allagash gas stovecomplies with and has been tested and listed as adirect vent heater and listed to ANSI Z21.88-1998(NFPA 54), and CSA 2.33-M98 for Canada.
DO NOT ATTEMPT TO ALTER OR MODIFYTHE CONSTRUCTION OF THE APPLIANCE
OR ITS COMPONENTS. ANY MODIFICATION OR ALTERATION WILL VOID THE
WARRANTY, CERTIFICATION AND LISTING
OF THIS APPLIANCE.

General Information• THIS HEATER MUST BE INSTALLED AND MAINTAINED BY A QUALIFIED SERVICE AGENCY.
• The installation and repair of this appliance must
be done by a qualified service person. Failure toproperly install and maintain this heater could
result in an unsafe or hazardous installation,
which may result in a fire, explosion, property
damage, personal injury or loss of life.
• This appliance should be inspected before use andat least annually. More frequent cleaning may berequired due to excessive lint from carpeting,bedding material, etc. It is imperative that control
compartments, burners and circulating air passageways of the appliance be kept clean.

established in the National Fuel Code, ANSI
Z223.1.(NFPA 54). In Canada, the codes have been
established in CAN/CGA B149 Fuel Installation
Code.
• Installer l’appareil selon les codes ou reglements
locaux, ou, en l’absence de tels reglements, selon
les Codes d’installation CAN/CGA-B149.
• DO NOT OPERATE THIS STOVE IF ANY PART HAS
BEEN UNDER WATER. Immediately call a qualified
service technician to inspect the heater and to
replace any part of the control system and any
gas control which has been under water.
• Ne pas se servir de cet appareil s’il a ete’ plonge
dans l’eau, completement ou en partie. Appeler
un technicien qualifie pour inspecter l’appareil etremplacer toute partie du syste’me de controle ettoute commande qui ont ete plonges dans l’eau.

Glass Front
Do not operate this appliance with the glass front
removed, cracked or broken. Replacement of theglass should be done by a licensed or qualified
service person. Only remove glass for routine
service. Always handle glass carefully.

• NOTE: THIS APPLIANCE MUST NOT BE CONNECTED
TO A CHIMNEY OR FLUE SERVING ANY OTHERAPPLIANCE.
• The installation must conform to local codes. Your
local Jøtul dealer can assist you in determining
what is required in your area for a safe and legal
installation. Some areas require a permit to
install a gas burning appliance. Always consult
your local building inspector or authority having
jurisdiction to determine what regulations apply
in your area.
• Your local officials have final authority in determining if a proposed installation is acceptable.
Any requirement that is requested by the local
authority having jurisdiction, that is not specifically addressed in THIS manual, defaults to local
code. In the absence of local codes, the installation requirements must comply with the current
National codes. In the U.S. these requirements are3

Safety Information

Location

This appliance will reach high surface temperaturesduring normal operation. Please read the following
notes to help ensure safe operation.

In selecting a location for the stove, consider thefollowing points:
1) Heat distribution2) Vent termination requirements
3) Gas supply line routing
4) Traffic areas, furniture, draperies, etc.

• Due to the high operating temperatures thisappliance should be located out of traffic andaway from furniture and draperies.

• Children and adults should be alerted to thehazards of high surface temperatures and should
stay away to avoid burns or clothing ignition.

• Young children should be supervised while they
are in the same room as the Allagash gas stove.

• Clothing or other flammable materials should not
be placed ON or NEAR the Allagash gas stove.
Surveiller les enfants. Garder les vetements, lesmeubles, l’essence ou autres liquides a vapeur
inflammables loin de l’appareil.

• NEVER store or use gasoline or any other flammable vapors or liquids in the vicinity of the
Allagash gas stove.

• Never burn any other materials in your Allagash
gas stove, it is strictly designed for use withnatural gas or propane fuel ONLY.

• Any safety screen, glass or guard removed for

The GF100 Nordic QT may be located on or nearconventional construction materials, however, proper
clearance to combustibles must be maintained inorder to provide adequate air circulation around theappliance. Also, it is important to provide adequate
access around the stove for servicing and proper
operation.
The clearance and hearth specifications listed inthis manual are the minimum requirements for
combustible material. A combustible material isanything that can burn (i.e. sheet rock, wall paper,
wood, fabrics etc.). These surfaces are not limited tothose that are visible and also include materials that
may be located behind non-combustibles.
If you are not sure of the combustible nature of amaterial, consult your local fire officials. Remember,“Fire Resistant” materials are considered combustible: they are difficult to ignite, but will burn. Also,“fire-rated” sheet rock is considered combustible.

servicing the appliance must be replaced prior tooperating the appliance.

Electrical Hazard

Hearth Requirements

When the Allagash gas stove is installed with theoptional forced air Blower Kit, the stove must be
electrically grounded in accordance with local codes
or, in the absence of local codes, with the current
NFPA 70- National Electrical Code or CSA C22.1Canadian Code.

The Allagash gas stove CAN NOT be installed directly
on carpeting, vinyl flooring, linoleum or Pergo®. If
you wish to install this appliance on any combustible
material OTHER THAN WOOD, a floor pad must be
installed that is either metal, wood or a listed hearth
pad. This floor protection must extend the full widthand depth of the appliance. It is not necessary to
remove the carpeting, vinyl or linoleum from underneath the floor protection.

The Allagash Blower Kit is supplied with a threeprong (grounding) plug for protection against shock
hazard and should be plugged directly into a properly
grounded three-prong receptacle.
DO NOT CUT OR REMOVE THE GROUNDING
PRONG FROM THE PLUG.
Always unplug the Blower Kit when performing
routine service to the Allagash gas stove.

4

Note: the hearth requirements are the same whenusing the optional short leg package.

Clearance Requirements
Minimum clearances for the GF3 DVII
Allagash
Rear:

Parallel Installation
4”
102 mm4” / 102 mm

Ceiling: 12” / 305 mm
Corner: 4” / 102 mm
Right Side: 4” / 102 mm
Left Side: 10” / 254 mm (required for complete
access of the lighting instructions)

Minimum Clearance for Vent Pipe
Horizontal Runs:
Off the top of the pipe:
Off the sides and bottom:

Right
Side
4”
102 mmLeft Side
10”
254
mm
2" (50mm)
1" (25 mm)

Vertical Runs, all sides: 1" (25 mm)

Figure 2. Allow 10” on left side of the appliance forcomplete access to the lighting instructions andcontrol valve.

Alcove Installation
Minimum Alcove Height:

40” / 1006 mm

Minimum Alcove Width:38” / 965 mm

Corner Installation(Assumes 10” off the left side and 4” off the right side)

Maximum Alcove Depth:

4”
102 mm24” / 607 mm

Pipe Clearances:1” on vertical runs2” off top of horizontal runs, 1” on other sides.

13 1/2”337 mm13 1/2”337 mm

16”
406
mm

36”
910 mmMantel and Trim Clearances
Mantel or Trim Depth24” / 607 mm
18” / 457 mm
AB

5” / 127 mm
C
Minimum
Clearance fromthe Top Plate
A = 12”27”
686 mmThis is not a required
hearth size, although it
is aesthetically
proportional. Assumes
the stove is 4” off thecorners.

4”
102 mm
16”
406 mmFigure 3. Top Exit Centerlines and possible hearth
configuration.

B = 9”
C = 4”

Figure 1.

5Venting Requirements

2 ft.
min.

There are two types of venting configurations
approved for use with the Allagash gas stove Horizontal Termination and Vertical Termination.
The GF3 DVII Allagash is approved for use withthe following vent components:
Simpson Dura-Vent GS
Secure Vent - Security Chimneys Intl. Ltd.
Amerivent Direct
Installation of any components not manufactured or approved by Jøtul or failure to meet all
clearance requirements will void all warranties andcould result in property damage, bodily injury, or
serious fire. Use parts from one manufacturer only DO NOT MIX VENT COMPONENTS FROM DIFFERENTMANUFACTURERS IN THE SAME SYSTEM.
The approved vent configurations describedherein are derived from extensive testing undercontrolled laboratory conditions. Gas appliance
performance can be negatively affected by variables
present in the installation environment, i.e: strong
prevailing winds, snow accumulation, etc. These
conditions should be taken into consideration by the
installer and stove owner.
IMPORTANT• JOINT SEALING REQUIREMENT: APPLY A 1/8” BEAD
OF HIGH-TEMPERATURE (750°F) SEALANT TO THE
MALE SECTION OF THE INNER VENT PIPE.
THE CEMENT SHOULD FORM A
SEAL BETWEEN THE INNER AND
OUTER PIPES.
• NEVER MODIFY ANY VENTINGCOMPONENT, OR USE ANY
DAMAGED VENTINGPRODUCT.
• FOLLO THE INSTALLATIONINSTRUCTIONS PROVIDED BY THE VENTMANUFACTURER FOR
EACH VENT PART.

2 ft.
min.

12

LowestDischarge
OpeningX
Roof Pitch
is X / 12

2 ft. = minimum height fromroof to lowest discharge opening

Figure 4. Vertical Vent Roof Penetration Height.

Vertical Venting Requirements (Vertical
Termination)• The minimum height of a vertically terminatedsystem shall be no less than 7'. The maximum
height shall be no more than 35'.

• With steep roofs, nearby trees, and predominant
windy conditions, poor draft or down draft
conditions can occur. In these cases, increasing theheight of the vent may improve the situation.

• If an offset or elbow is necessary in the verticalrise, it is important to support the vent pipe every
three feet, to avoid excessive stress on the offsets.
Jøtul recommends the use of Simpson Dura-Vent’s
Wall Straps. (#988).

• Whenever possible use 45° elbows opposed to 90°
elbows. This offers less restrictions for the flow offlue gases and intake air.
NOTE: Vertical termination may result in reduced
flame height and heat output due to the “suction”
of natural draft.

• Vertical Termination Height: In no case shall any

SE

AL

AN

T

• THE GAS APPLIANCE AND VENT SYSTEM MUST BE
VENTED DIRECTLY TO THE OUTSIDE OF THE BUILDING AND NEVER ATTACHED TO A CHIMNEY SERVING A SOLID FUEL OR GAS BURNING APPLIANCE.
EACH DIRECT VENT GAS APPLIANCE MUST HAVE ITSOWN SEPARATE VENT SYSTEM. COMMON VENTSYSTEMS ARE PROHIBITED.
• IF VENTING SYSTEM IS DISASSEMBLED FOR ANY
REASON, REINSTALL PER THE INSTRUCTIONSPROVIDED FOR THE INITIAL INSTALLATION.

6

Termination
Cap

2 ft.
min.

Vertical Wall

Horizontal Overhang

discharge opening on the cap be less than 2' (610mm) horizontally from the roof surface. See Figure 4.

• A firestop is required at every floor. The opening
should be framed to 10" X 10" inside dimension.
Jøtul recommends the use of Simpson Dura-Vent
Firestop (#963).

• Any venting that is exposed above the first floor,
regardless of attic space or living space, must be
enclosed. Always maintain the required 1" clearance from all sides of the vertical vent system.

• It may be necessary to add restriction to a verticalventing installation, so that the draft is not too
strong and creates incomplete combustion.
The Allagash is equipped with sliding restriction
plates that can be adjusted to compensate forexcessive draft. See Figure 5.

Restrictor Sliders
12
12

12
12
12

First Restriction
Setting - installscrew into the
OUTER hole ofsliders.
Second Restriction
Setting - screw
installed into
MIDDLE hole ofslider.

Wall
Thimble#942B

Horizontal Length12” Max.

Wall Plate#940B

90° Elbow#990B
24” length#904B
55 3/4”
Floor tocenterline ofminimum
vertical rise

Figure 5. Vent restrictor settings.

Horizontal Venting Requirements

NOTE:
SHORT LEGSREDUCE THE
HEIGHT BY
2 1/4”.

Follow these guidelines if any part of the installation
incorporates a horizontal run or terminates horizontally.
• The maximum horizontal run made directly off therear of the stove shall be no more than 12" and mustthen be connected to a 14" snorkel cap (Simpson Duravent #982).
• The horizontal termination cap must maintain a 3"
clearance to any overhead combustible projections
exceeding 2 1/2" or less. Maintain 12" clearance fromprojections exceeding 2 1/2". See Figure 8, page forcomplete termination clearance information.

Figure 6. Minimum Vertical Vent - Simpson DuraVent part numbers shown.
Simpson Dura-Vent 45°
Elbow #945B• Any horizontal run of vent must be level or have a 1/
4" rise for every foot of run toward the termination
cap.

123
123
123
123
123
123
123 12” Max.
Horizontal run
into a 14”
SnorkelSimpson DuraVent (#906B)

NEVER ALLOW THE VENTING TO SLOPE DOWNWARD,
AS HIGH TEMPERATURES MAY RESULT AND CREATE A
HAZARDOUS CONDITION.
• Vent Pipe Clearance to Combustible Materials: For all
horizontal runs, a 2" top clearance and a 1" side andbottom clearance must be maintained.
• Wall Pass-through: A minimum 10" X 10" squarecutout is required to maintain proper clearances
through combustible wall construction. The opening
must be framed in. Simpson Dura-Vent Wall Thimble#942 or Secure Vent Wall Radiation Shield SV4RSM
must be used for the wall pass-through. Optional
decorative plates are available to finish the interiorside of the wall pass-through.

Figure 7. Horizontal terminal to corner.

12” Max. Horizontal
run into a 14” Snorkel
Simpson Dura-Vent(#906B)

14” Snorkel
SimpsonDura-Vent(#982)• IMPORTANT: Follow the vent manufacturer’s installation instructions provided with each vent component.
• DO NOT FILL AIR SPACE WITH ANY TYPE OF INSULATION.
• MAINTAIN THE PROPER CLEARANCES TO THE TERMINATION CAP. SEE FIG. 10.
• Do not recess the termination cap into a wall orsiding.
• Install a Vinyl Siding Standoff between the vent cap
and the exterior wall (Simpson Dura-Vent #950). toprotect vinyl siding from overheating.

Rear Exit
Centerline
24 3/4”628 mmFigure 7a. Horizontal terminal directly off stovemust use a 14” Snorkel termination.

7

A DIRECT VENTTERMINATION KITAND CAP ISREQUIRED TO
ALLOW FRESH AIR
INTO THE CHIMNEY.

Co-linear Vent Installation
The GF 3 DV Allagash may be vented through amasonry or Class A prefabricated chimney using a
Co-linear Flexible Vent system approved for use witha solid-fuel burning fireplace, When installed in themanner described below, this system can improve
the performance of the appliance in cold climate
situations, as well as simplify the vent installation.
These guidelines must be followed:
1. Prior to the installation the chimney flue must be
thoroughly cleaned and inspected by a qualified
chimney service person.
2. In a masonry chimney, a fireclay liner must bepresent the entire length of the chimney.
3. Prefabricated chimneys must be UL 103 or ULC S629 listed and have a minimum INSIDE diameterof 6 inches, (150 mm).
4. No appliance can be installed into a chimney flue
serving any other appliance of any kind.
5. THE AIR INTAKE FLEX PIPE MUST EXTEND BEYOND
THE DAMPER AREA OF THE FIREPLACE.
6. If the intake flex does not extend the full length ofthe chimney and connect to both the unit and thetermination cap, A METAL BLOCK OFF PLATE MUST
BE CONSTRUCTED AND INSTALLED ABOVE THE
UNIT PRIOR TO THE END OF THE INTAKE FLEX AND
MUST COMPLETELY SEAL THE CHIMNEY FLUE
FROM THE ROOM.
Consult with the local code authority having
jurisdiction before proceeding with this type of
installation.
Refer to the vent manufacturer’s instructions for
specific installation requirements.
WARNING: FAILURE TO POSITION THE PARTS ANDSTOVE IN ACCORDANCE WITH THESE DIAGRAMS OR
FAILURE TO USE ONLY PARTS SPECIFICALLY APPROVEDFOR USE WITH THIS APPLIANCE MAY RESULT IN
PROPERTY DAMAGE OR PERSONAL INJURY. BE SURETO MAINTAIN THE PROPER CLEARANCES TO COMBUSTIBLES AS DEFINED IN THIS MANUAL AND IN THE
INSTRUCTIONS PROVIDED WITH EACH VENT COMPONENT.

EXHAUST
GAS
Fireclay liner must
exist through theentire length ofthe chimney

FRESH AIR

Exhaust flex pipe
must extend theentire length of thechimney andconnected to a direct
vent termination
AIR INTAKE flex
pipe must
be a
The Air Intake Flex
minimum of 6 ft.
pipe must extend(457 beyondcm) andtheextend beyond thedamper.
damper area

FIREPLACEDAM PER AREA

A metal blockoff plate mustcompletely seal
the chimney
from the room.

Figure 8. Co-linear Vent installed throughmasonrychimney.

24 3/4”to centerof flue collar

28 3/4”to top of
Co-linear
Adapter.

Figure 8a. Co-linear Adaptor centerline.

8

Simpson Dura-Vent Chimney
Conversion Kit
The GF3 DVII Allagash is approved for use with
Simpson Dura-vent Chimney Kit as shown in Figure
9. These installation requirements must be followed:
1. In masonry chimney a fireclay liner must bepresent the entire length of the chimney.

Vertical Termination
Cap #991(Not included in kit).
Simpson Dura-Vent
Termination Kit
GF 3 DVALLAGASH
Stove

2. The liner must have an inside dimension of 6”
round or greater. (USE KIT #934)
3. Prefabricated chimneys must be listed for the
specific Simpson Dura-Vent Chimney Conversion
Kit or a UL 103 listing. (USE KIT #931, #932, or#933)
4. When venting immediately off the rear of the
Allagash the maximum horizontal must be lessthan 14” (including thimble depth). Any otherhorizontal must be less than 24“.
5. Restrictor plates, shipped with the stove, should
be installed according to the assembly instructions in this manual.

Mobile Home Installation
The Allagash can be installed for use in a mobile
home in the U.S. and Canada provided:
1. The stove is secured to the floor of the mobile
home. Use Floor Mounting Kit #750304.
2. The stove is installed in accordance with Title 24
CFR, Part 3280- Manufactured Home Construction and Safety Standard, in the U.S. and in
Canada, comply with CSA Z240.4, Gas Equipped
Recreational Vehicles and Mobile Housing.

Simpson Dura-Vent
Thimble Adapter(Included in kit)

4 inch(100 mm)
Flex Liner(Not included in
kit)

Simpson Dura-Vent#990 90º Elbow .
(Not included in kit).
Appropriate length ofSimpsonDura-Vent Pipe forvertical rise.
(Not included in kit).
A: M aximum
horizontal run whenventing immediately
off the rear of thestove MUST BE LESS
THAN 14” (360 mm)
TOTAL!

Fire-clay
liner or UL
103 listed
prefabricated chimney pipe.

A

Figure 9. GF 3 DVII Allagash vent connection using
Simpson Dura-Vent Chimney Conversion Kit.

3. Always contact your local officials about installation restrictions and requirements in your area.
This appliance may be installed as an OEM
Iinstallation in manufactured (mobile)homes andmust be installed according to the manufacturer’s
instructions and the manufactured home construction and safety standard, Title 24 CFRAND SAFETY
STANDARD, TITLE 24 CFR, Part 3280. This appliance isonly for use withthe type of gas that is indicated on
the stove Rating Plate. A gas conversion kit isprovided with the GF3 DVII Allagash gas stove.
This appliance may be installed in an aftermarket permanently located, manufactured, (mobile)home, where not prohibited by local codes.
Cet appareil peut etre installe dans un maison
prefabriquee (mobile) deja installee a demeure si lesreglements locaux le permettent. Cet appareil doit etre
utilise uniquement avec les types de gas indiques sur laplaque signaletique. Ne pas l’utiliser avec d’autres gas sauf
si un kitde conversion certifie est installe.

IMPORTANT NOTICETHE USE OF AN EXISTING CHIMNEY
AS AN AIR INTAKE IS NOT COVEREDUNDER THE ANSI Z21.88-1999-CSA
2.33-M99 TEST METHODS AND RESULTING ITS/WHI PRODUCT CERTIFICATION. THE CODE AUTHORITYHAVING JURISDICTION MUST BE
CONSULTED PRIOR TO PROCEEDING
WITH THIS INSTALLATION METHOD.

9

Vent Termination Window

Max.
35
VerticalTermination Height

VENTING MUST TERMINATE
WITHIN THE SHADED AREAS.

30
REMINDER #1
Any horizontal runs madedirectly off the rear of the stovemust be 14” or less and connected immediately to a
Simpson Dura-Vent 14” snorkel(#982).

25

REMINDER #2
If more than a 12” horizontal run
is needed, A VERTICAL RISE ISREQUIRED FIRST. See chart.

For each 90° elbow used, after
the first, add 5’ to the initialrequired vertical rise. See chart.
Maximum 90° Elbows - 3
Maximum 45° Elbows - 4

VERTICAL RISE in feet

REMINDER #3

20

15

10
VerticalTermination
requires 7 ft.
Min. Rise.

7
5

Horizontal
Termination
requires 2 ft.
Min. Rise.

2

12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
1234567890123456789012345678901212345678
12345678901234567890123456789012123456789012345678901234567890

Use second
restriction
setting in thisshaded area.
See Page 81234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
Use first restriction setting
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
for termination in this1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
shadedarea. See page 81234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
1234567890123456789012345678901212345678
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890
12345678901234567890123456789012123456789012345678901234567890

1Min./Max.
Horizontal
with 12” rise

10

10
5
HORIZONTAL RUN in feet

Vent Terminal Clearances

Figure 10. Vent Terminal Clearances - National Fuel Gas Code.
A = Clearance above grade, veranda, porch , deck, or
balcony : *12 inches (30 cm) minimum.
B = Clearance to window or door that may be opened:
9 inches (23 cm) minimum. 12 inches is recommended to help prevent condensation.
C = Recommended clearance to permanently closed
window: mimimum 12 inches (30 cm) to help
prevent condensation on the window.
D = Vertical clearance to ventilated soffit located above
the terminal within a horizontal distance of 2 feet (60cm) from the centerline of the terminal: 18 inches(46 cm) minimum.
E = Clearance to unventilated soffit: 12 inches (46 cm)
minimum.
F = Clearance to outside corner: 9 inches (23 cm) min.
Jøtul N.A. strongly recommends 12 inches (30 cm),
particularly where windy conditions are prevalent.

G = Clearance to inside corner: 6 inches (16 cm) min.
Jøtul N.A. strongly recommends 12 inches (30 cm), particularly
where windy conditions are prevalent.

H = *Not to be installed above a meter/regulator assembly
within 3 feet (90 cm) horizontally from the center-lineof the regulator.
I = Clearance to service regulator vent outlet: 6 feet (1.8m) minimum.
J = Clearance to nonmechanical air supply inlet to buildingor the combustion air inlet to any other appliance:*12 inches (30 cm) minimum.
K = Clearance to a mechanical air supply inlet: *6 feet
(1.8 m) minimum.
L = ** Clearance above paved sidewalk or a paved driveway
located on public property: *7 feet (2.1 m) min.
M = Clearance under veranda, porch, deck, or balcony:*12 inches (30 cm) minimum. 1*

As specified in CGA B149 Installation Codes. Note: Local Codesand Regulations may require different clearances.
** A vent shall not terminate directly above a sidewalk or
driveway which is located between two single family dwellings
and serves both dwellings.*
1
Only permitted if veranda, porch, deck, or balcony, is fully open
on a minimum of two sides beneath the floor.*

12 
305
mm

2 1/2
64 mm
3
76 mm

Figure 11. Vent Terminal / Overhang Clearances

11Fuel Conversion
The Allagash gas stove is shipped from the factoryequipped as a NATURAL GAS unit; However, thestove is shipped with the necessary gas conversion
kit to convert the stove to burn propane gas. The kit
contains all the necessary components needed tocomplete the conversion and ensure safe operation,
including Conversion Notice labels that must be
affixed to the stove and stove Rating Plate.

IN CANADA: THE CONVERSION SHALL BE CARRIEDOUT IN ACCORDANCE WITH THE REQUIREMENTS OF
THE PROVINCIAL AUTHORITIES HAVING JURISDICTION AND IN ACCORDANCE WITH THE REQUIREMENTS OF THE CAN1-B149.1 AND .2 INSTALLATIONCODE.

WARNING:THE CONVERSION KIT IS TO BE INSTALLED BY AN AUTHORIZED JØTULSERVICE TECHNICIAN IN ACCORDANCEWITH THE MANUFACTURER’S INSTRUCTION AND ALL CODES AND REQUIREMENTS OF THE AUTHORITY HAVINGJURISDICTION. FAILURE TO FOLLOWTHESE INSTRUCTIONS COULD RESULT IN
SERIOUS INJURY OR PROPERTY DAMAGE.
THE QUALIFIED AGENCY PERFORMING
THIS WORK ASSUMES RESPONSIBILITY
FOR THIS CONVERSION.

1. Turn off gas supply to the stove.

Tools required:• 1/4” Nut driver• 7/16” open end wrench• 1/2” open end wrench • Torx T-20 or slot headscrewdriver.

Kit Contents:
1, Regulator Tower labeled for propane
3, Regulator Tower screws
1, Burner Orifice (1.5 mm for LPG, #38 for NG)
1, Pilot Orifice ( #30 for LPG, #51 for NG)
1, 4 mm Hex Key
Label A - to be completed and applied to the back of
the stove.
Label B - apply to the stove Rating Plate.

IMPORTANT: SHUT OFF THE GAS
SUPPLY AT THE MAIN SUPPLY VALVEBEFORE BEGINNING THE
CONVERSION.
If a blower is installed, be sure to
disconnect the power cord before
proceeding with this conversion.

Gas Conversion Procedure
2. Open the front doors.
3. Remove the stove top plate.
4. Release the glass clips atop the stove andslowly lift glass panel up and off of the firebox.
5. Carefully remove the logs and set out of the way.
6. Remove burner tube: Lift out the log support plate.
Using a ¼” nut driver remove the two screws securing the burner tube (17, pg. 22) to the stovebottom. Lift out the burner tube.
7. Change the main burner orifice (32, pg 22 andFig. 12). Using a ½” open end wrench, remove
the burner orifice and replace with the appropriate orifice, supplied in the kit.
Natural gas - #38
Propane - 1.5 mm DMS
8. Adjust the air shutter on the burner tube toallow for the proper mixing of air and gas. See
Fig. 12.
Natural - Three-quarters OPEN.
Propane - FULL OPEN
9. Change the pilot orifice. From within the firebox,
pull the spring clip back and remove the Pilot
Head from the Pilot Base. Use the 4 mm hex key
to remove the old Pilot Orifice from the base(counterclockwise). See Fig. 13.

NOTE: The Air Shutter should never be set LESS
than 1/8” open.

Burner Tube

Air
ShutterBurner Orifice

Figure 12. Burner Orifice and Air Shutter. Shutter isshown in the fully open position.

12

Screws
Replace with the appropriate pilot orifice.
#51 for natural gas#30 for propane
Be certain the orifice is securely tightened.
Replace the Pilot Hood into the base.
12. Replace the Variable Regulator: Using a Torx T20 screwdriver, remove the three specialty screws
from the front of the valve regulator. See Fig. 14.

Regulator Tower

Gasket13. Remove the regulator tower and the old blackgasket.
14. Ensure that the new gasket is properly positioned and install the new variable regulator
tower. Tighten screws securely. Apply the small
valve label to the valve body where it will beeasily seen.
15. Reinstall the Burner Tube (13, pg. 22), Air Divider(15), Log Support (14), and Log Set. WHEN
REINSTALLING THE BURNER TUBE, BE SURE THE
TUBE IS PULLED FORWARD IN THE MOUNTING
HOLES. SECURE WITH THE TWO 1/4” SCREWS.
16. Apply the two conversion labels to the stove
and rating plate so that they can be seen byanyone servicing the stove.
17. Reassemble the stove, open the gas supply andcheck for leaks using a 50/50 soapy water
solution. NEVER USE AN OPEN FLAME TO CHECKFOR GAS LEAKS.

Figure 14. Regulator tower and gasket.

Correct gas pressure is essential for efficient andsafe operation of the Allagash gas stove. It is
important that the correct gas pressure be established at the time of the installation. For moredetails see the Gas Pressure section of this manual.

Pilot Hood
Pilot Orifice

ALWAYS REFER TO THE LIGHTINGINSTRUCTIONS ON THE INSIDE BACK
COVER OF THIS MANUAL AND ON THE
BACK OF THE RATING PLATE.

Pilot Base
Figure 13. Removing the Pilot Hood and Pilot Orifice.

13

Gas Connection
NOTE: IF THE OPTIONAL BLOWER KIT (# 129161) IS
TO BE INSTALLED ON THE STOVE AT THE TIME OF THE
INSTALLATION OR IN THE FUTURE, THE GAS SUPPLYLINE SHOULD BE INSTALLED AS CLOSE TO THE FLOOR
AS POSSIBLE. USE OF A 90° ELBOW DIRECTLY OFF THE
VALVE TO ALLOW FOR ADEQUATE CLEARANCE FOR
THE BLOWER. See Figure 15.
The gas supply line connection is made to thevalve just inside the left rear leg. The Gas supply line
should be 3/8" or 1/2" diameter, or the appropriate
size to provide sufficient gas pressure to the valve
regardless of the input setting.
The use of Flexible Gas Appliance Connectors is
acceptable in many areas in the U.S., however,Canadian methods vary depending on local code.
ALL INSTALLATIONS MUST COMPLY WITH LOCALCODE OR IN THE ABSENCE OF LOCAL CODE, MUSTCOMPLY WITH THE MOST RECENT EDITION OF THE
NATIONAL FUEL GAS CODE ANSI Z223.1/NFPA 54 OR
CAN-B149. THIS APPLIANCE MUST BE INSTALLED BY A
LICENSED MASTER OR JOURNEYMAN PLUMBER OR
GAS-FITTER WHEN INSTALLED IN THE COMMONWEALTH OF MASSACHUSETTS.
All codes require: a gas shutoff valve (gas cock)and union, to be installed in the supply line, and in
the same room as the appliance. This allows for the
disconnection of the stove for servicing and maintenance. See Figure 15.
A T-HANDLE GAS COCK IS REQUIRED IN
MASSACHUSETTS IN COMPLIANCE
WITH CODE 248 CMR.

Secure all joints tightly using appropriate tools
and sealing compounds (for propane units be sure touse compounds that are propane resistant). Turn on
gas supply and test for gas leaks using a soapy water
solution. Never use an open flame to check for leaks.

Leak test:
1. Mix a 50-50 solution of water and dish soap.
2. Light appliance- see lighting instructions on page
22 of this manual or on the stove’s rating plate.
3. Brush or spray all joints and connections with thesoapy water solution.
4. If bubbles appear at any connection or seam or agas odor is detected immediately turn gas control
knob to the OFF position.
5. Tighten or reconnect the leaking joint and retest
for any gas leaks.

Gas Pressure
Correct gas pressure is essential for efficient andsafe operation of the Allagash gas stove. It is
important that the correct pressure is established at
the time of the installation. Proper gas pressure
provides a consistent flow of gas to the applianceand is instrumental in checking for gas leaks. The gas
control valve on the stove is equipped with pressure
test points for gauge connections. The gauge
connections are located on the front of the valve
under the On/Off/Pilot- knob. See Fig. 16. Gauge
connections are identified by:• E for inlet or supply pressure ( the amount of gas
coming to the valve.)• A for manifold pressure (the amount of gas thatis coming out of the valve to the burner.)
Control ValveE
A
Figure 16. Inlet and Manifold pressure test points.

INLET GAS PRESSURES(inches water column)

Figure 15. Gas supply valve types and fittings.

14

NATURAL GASPROPANEMIN

MAX

5.0 WC
11.0 WC

7.0 WC
13.5 WCALWAYS TEST PRESSURES WITH VALVE CONTROLKNOB SET ON HIGH.
The appliance must be isolated from the gas
supply line by closing its individual manual gas
shutoff valve (gas cock) during any pressure testingof the gas supply piping system that is equal to or
exceeds pressures of 1/2 psig. (3.5 kPa).

High Altitude Orifice Chart
Elevation

Fuel

Orifice
SizePart No.

0 - 2000 ft.
(0 - 610 m)

Natural Gas #38
Propane
1.5 mm129130129146

2001 - 4500 ft.
(611 - 1370 m)

Natural Gas
PropaneDo Not Derate
754517P#38#54

High Altitude Adjustment
Installation at high altitude locations (above 2500'),
makes it necessary to compensate for the thinnerair (less volume of air per cubic foot). Higher altitudes affect the atmospheric pressure and heatvalue of some gaseous fuels. The Allagash DVII
requires adjustment for Propane fuel at high altitude, but not for Natural gas.

Derating Procedure

In the U.S.

2. Remove the burner tube/log support to expose
the main burner orifice.

THE DERATING KIT MUST BE INSTALLED BY AN
AUTHORIZED SERVICE TECHNICIAN IN ACCORDANCEWITH THE MANUFACTURER’S INSTRUCTIONS AND
ALL CODES AND REQUIREMENTS OF THE AUTHORITYHAVING JURISDICTION. THE INFORMATION STICKER
MUST BE FILLED OUT BY THE INSTALLER AND ADHERED TO THE APPLIANCE AT THE TIME OF THE
CONVERSION. THE QUALIFIED SERVICE AGENCYPERFORMING THIS WORK ASSUMES RESPONSIBILITY
FOR THIS DERATING.

To derate this unit, install the appropriate orifice per
the High Altitude chart.
1. Remove the two ¼” hex head screw that holds
the burner tube/log support to the bottom of thestove.

3. Remove the orifice and replace with the appropriate one from the high altitude kit.
4. Be sure to attach the high altitude conversion
sticker provided with the kit to the rating plate on
the appliance.

For installations from 610 - 1370 meters (20004500 ft.) the orifice size for natural gas is #38 and for
propane gas #54.

THIS STOVE HAS BEEN CONVERTED FOR USE AT
AN ALTITUDE OF: ___________

SEE THE HIGH ALTITUDE ORIFICE CHART ON THIS
PAGE.

Orifice Size: __________ Manifold Press. _____

See the stove Rating Plate for additional information. For high altitude installations consult the
local gas distributor or the authority having jurisdiction for proper rating methods. If the installer must
convert the unit to adjust for varying altitudes, theinformation sticker must be filled out by the installer and applied to the appliance at the time of
the conversion.

Input Btu/Hr. _________ Fuel Type __________
Date of Conversion ___________
Figure 17. High Altitude Conversion Label. This sticker
is included in all high altitude kits and must be
applied to the stove when converted for high altitude.

In Canada:This unit has been tested for installation at highaltitudes in accordance with Canadian test standard
CAN/CGA-2.17.
THE DERATING SHALL BE CARRIED OUT IN ACCORDANCE WITH THE REQUIREMENTS OF THE PROVINCIAL AUTHORITIES HAVING JURISDICTION AND IN
ACCORDANCE WITH THE REQUIREMENTS OF THE
CAN1-B-149.1 AND .2 INSTALLATION CODE.

15

Air Shutter & Flame Picture
Adjustment

Log Set Installation

The GF3 DVII Allagash is shipped from thefactory equipped to use NATURAL GAS. If the stove isconverted to use Propane, it will be necessary toadjust the air shutter on the burner tube to achieve
the proper gas to air mix. THE AIR SHUTTER SHOULD
BE SET FULL OPEN FOR PROPANE USE AND THREEQUARTERS OPEN FOR NATURAL GAS USE.

The Allagash is equipped a one piece log set and ispackaged in bubble wrap inside the firebox. The log
set must be removed from the packaging andarranged in the unit prior to start up of the gas
stove. Do not handle the log set with your barehands. Always wear gloves to prevent skin irritationfrom the ceramic fibers.

The air shutter can also help achieve the desired
flame appearance. Generally, flame appearance is amatter of preference, however most people enjoy awarm, yellowish flame.

To install the log set, remove the packaging andplace the log set inside the firebox, centered fromleft to right and completely against the rear wall of
the stove. See Fig. 18.

Too large a setting: The appliance will generate aflame that is blue and transparent, or an “anemic”
flame.

Also, the stove is shipped with a package of
Glowing Embers. These are to be individuallysprinkled across the screen above the burner tube.
It is best to equally space these embers for optimum flame appearance. Note: All of the embers do
not need to be used.

Too small a setting: The appliance will generatevery long yellow flames resulting in soot. Sooting
produces black deposits on the logs, on the insidewalls of the appliance, and potentially on theexterior termination cap. See Fig. 12 for reference.
Sooting is caused by incomplete combustion in
the flames and lack of combustion air entering the
air shutter opening.

CONTACT WITH THE CERAMIC FIBER LOGS ANDGLOWING EMBERS MAY CAUSE SKIN IRRITATION.
SHOULD THAT OCCUR, GENTLY WASH HANDS WITH
WARM SOAPY WATER.

To adjust the air shutter: remove the burner
tube and using a phillips head screwdriver loosen
the screw at the air shutter and adjust accordingly.
Be sure to retighten the screw that holds the air
shutter setting. Reassemble the stove and close thedoor, allow stove to burn 30 minutes on the HIGH
setting, observing the flame continuously. If theflame appears weak, slow, or sooty, repeat theprocess described above until the flame is as desired.

WARNING:AIR SHUTTER ADJUSTMENTS SHOULD
ONLY BE PERFORMED BY A QUALIFIEDPROFESSIONAL SERVICE TECHNICIAN.

16

Figure 18. Proper flame picture.

Optional Blower Installation
IMPORTANT: IF THE OPTIONALFORCED BLOWER KIT(PART # 129161)
IS TO BE INSTALLED ON THE STOVEAT THE TIME OF THE INSTALLATIONOR IN THE FUTURE, THE GAS SUPPLYLINE SHOULD BE INSTALLED AS
CLOSE TO THE FLOOR AS POSSIBLE.
USE OF A 90° DIRECTLY OFF THE
VALVE WILL ALLOW FOR PROPER
CLEARANCE FOR THE BLOWER. SEE
FIG. 18.
Blower Kit Contents:• Blower with mounting bracket• Snapstat and Wiring Harness• Hi/Low/Off Switch• two 6mm bolts

BlowerGas Line

90° elbow installed
directly off valve to
avoid blower

Figure 19. Blower and gas line installation.

Attach the Blower
1. Locate the two raised bosses on the bottom backof the stove. See Figure 19. The blower ismounted to the stove using these two threadedholes.
2. With the blower bracket and snapstat facing
upward, align the two middle mounting holeson the bracket with the two threaded holes on
the bottom back of the stove.
3. Use the two 6mm bolts to attach the blower tothe stove. Be sure to tighten the bolts so thatthe blower is drawn upward and tight against
the stove bottom.

Figure 20. Blower attachment points.

4. The snapstat (thermodisc), attached to theblower bracket, should be inserted under thestove bottom to make contact with the firebox!

Connect the Blower Wiring Harness
1. Lift off the stove top plate.
2. Loosen (BUT DO NOT REMOVE) the 10 mm bolt holding
the switch box to the side of the stove (left rearcorner of the stove), and lift out the switch box.
3. Remove the “blank” switch from the box. (Hint:
break the retaining tabs holding the switch in thebox.)

Figure 21. Blower position installed.

4. Insert the new HI/OFF/LO switch into the box.
5. Connect the insulated wires from the blower tothree leads on the HI/OFF/LO switch. BLACK wire
to the HI position, WHITE wire to the OFF position,and the RED wire to the LO position. See Fig. 22.
6. Reattach the switch box to the side of the stove.
Be sure all wires are unobstructed.
7. Replace top plate.

The blower will ONLY come on when the switch is in
the Hi or Low position and ONLY when the snapstat(thermodisc) is heated by the operation of the stove.
(Approximately 10- 20 minutes after the stove has
been running).

17

Snapstat(attached toblower bracket)
BLOWERHI/LO
SWITCHPlug

CAUTION:LABEL ALL WIRES PRIOR TO
DISCONNECTION WHEN SERVICING
THE CONTROLS. WIRING ERRORSCAN CAUSE IMPROPER AND
DANGEROUS OPERATION. ALWAYSVERIFY PROPER OPERATION AFTERSERVICING THE APPLIANCE.

Wire Harness

Figure 22. Attaching the blower wire harness.
THERMOPILE

ROCKERSWITCHON

Optional Wall Thermostat or
Remote Control
When installing a wall mounted thermostat to the
Allagash it must be 750 millivolt DC two-wire circuitthermostat. The thermostat should be placed in thesame room as the heater, typically 5’ off the floor.
Avoid drafty areas or any area that may effect theaccuracy of the thermostat.
The thermostat should be connected to the
Allagash using a minimum of 16 gauge wire with amaximum length of 35 feet of wire.
Connect the two thermostat wire leads to thetwo lower terminals on the terminal block locateddirectly above the ignitor button. Do not overtighten
the connections. IT IS NOT NECESSARY TO DISCONNECT ANY OTHER WIRES. See Figure 23.
For the thermostat to work the On/Off/T-Statswitch on the back of the stove must be in the T-stat
position, and the pilot light must be running, for it is
the power source for the thermostat.
At the thermostat the two wires should beconnected to the two connections screws on thethermostat base plate per the manufacturer’s
instructions.

Remote Control
The remote receiver should be wired to the terminal
block the same as the thermostat. See the instructions above.

18

TH

OFF

TP

STAT

TH
TP

OPTIONAL
THERMOSTATorREMOTECONTROLVALVETERMINAL
BLOCK

Figure 23. Wiring Diagram / Remote or Thermostat

System Check
1. PURGE THE GAS LINE: When lighting the appliance for the first time it will take a few moments toclear the gas line of air. Once this purge is complete,
the appliance will operate as described in thelighting instructions located on the stove’s ratingplate. All subsequent lightings of the stove will not
require such purging of the gas line.

CAUTION: DO NOT ATTEMPT TO ALTER THE
FLAME APPEARANCE BY POSITIONING THE
GAS VALVE IN ANY OTHER POSITIONOTHER THAN THE FULL “ON” POSITION.

2. PILOT FLAME: The pilot flame should be steady,not lifting or floating. The flame should be blue incolor around the pilot hood, with traces of yellow
toward the outer edges.
The pilot flame should engulf the top 3/8” of thethermopile (for millivolt generation) and the top 1/
8” of the thermocouple. The pilot flame should
project out of the pilot hood 1” at all three port. See
Figure 24.
1
(25mm)
1/8
(3mm)
Min.

3 - 4

3 - 4

1 - 2
3/8
(8mm)
Min.

Figure 25. Correct flame appearance on High setting
after approximately 15 to 20 minutes operation.

Pilot
assembly

Figure 24. Correct Pilot Flame
Burner tube

3. BURNER ADJUSTMENT: The GF3 DVII Allagash gas
stove is equipped with a variable gas control valve.
This valve provides easy adjustment of the flame
height appearance and heat output. To adjust theflame between the HI and LOW setting, rotate the
HI/LOW knob, located in the center of the valve face.
Flame height will adjust approximately 1.0” to 1.5”
between the HI and LOW settings. See Figure 25.
NO SMOKE OR SOOT SHOULD BE PRESENT.
CHECK LOG PLACEMENT IF ANY SOOT OR SMOKE IS
DETECTED. IF SOOT OR SMOKE PERSIST, THE AIRSHUTTER MAY NEED TO BE ADJUSTED. See Air
Shutter/Flame Appearance section of this manualfor proper air shutter settings and adjustments.
Note: The more offsets there are in the vent system,
the greater the need for an air shutter adjustment.

Ignitor123
123121212
12
12
12
Thermopile

Thermocouple

Figure 26. Pilot Assembly location.
WARNING: AIR SHUTTER ADJUSTMENTSSHOULD ONLY BE PERFORMED BY AQUALIFIED PROFESSIONAL SERVICE TECHNICIAN.

19

Operation

Maintenance

1. The Allagash is equipped with an On/Off/T-statrocker switch or can be controlled using an
optional wall mounted thermostat. A separate
switch is provided for the optional forced air
blower kit.

The Allagash Direct Vent gas stove and its venting
system should be inspected before use and at least
annually by a qualified service technician.

2. When lit for the first time, the stove will emit anodor for several hours. This odor results frompaint curing and the burn-off of manufacturingresidues. This condition can be alleviated by
opening a window to allow fresh air circulation
during this break-in period.
3. Condensation may occur on the glass each time
the burner is turned on. This fog will disappear as
the appliance becomes hot.
4. Keep the controls and the area under the appliance free of debris, vacuum this area frequently.
Always keep the appliance area clear and freefrom combustible materials, gasoline and otherflammable liquids.
If and when a vacuum is used on any service forthe stove, ALWAYS be sure the stove is OFF.
5. Remember, this appliance has a continuously
burning pilot flame. Exercise caution when using
products with combustible vapors.
6. CAUTION: DO NOT OPERATE THIS APPLIANCE
WITH THE GLASS REMOVED CRACKED OR BROKEN.
REPLACEMENT OF THE GLASS SHOULD BE DONE
BY A LICENSED OR QUALIFIED SERVICE PERSON.
USE ONLY REPLACEMENT GLASS PROVIDED BYYOUR AUTHORIZED JØTUL DEALER. NEVER USE
ANY SUBSTITUTE MATERIALS.

IMPORTANT:BEFORE ANY SERVICE WORK IS PERFORMED ON THE STOVE, ALWAYS TURN
OFF THE GAS SUPPLY TO THE STOVE AND
UNPLUG THE BLOWER IF INSTALLED.

General Cleaning:
The firebox should be vacuumed annually toremove any surface build up. Be sure to vacuum orwipe off the pilot assembly and burner orifice andburner tube. Also, when vacuuming the log set, besure to handle it carefully as it is very fragile.

Gasket Inspection:
It is important that the glass gasket be inspected atleast annually. Examine the rope gasket for signs ofdeterioration and make sure the gasket has apositive seal. This is important to prevent combustion gases from escaping into the room. Replace
the gasket if necessary, refer to the replacement
parts list on page 23.
Always replace any damaged or broken parts on
the Allagash with JØTUL AUTHORIZED PARTS ONLY.
These are available through your Jøtul dealer. Neveruse any substitute parts on your Allagash Direct
Vent stove.

Glass Care:NOTE: Anyone using this applianceshould follow the Lighting Instructions
located on the inside back cover of thismanual.
The Lighting Instructions are also locatedon the back of the stove Rating Plateattached to the bottom of the stove.

Clean the glass only when necessary. Wipe surface
with a clean, dampened, soft cloth. Follow with adry, soft towel as desired. Take care not to scratch
the glass surface.
WARNING: DO NOT USE ABRASIVE CLEANERS ON
THE GLASS. NEVER CLEAN THE GLASS WHEN IT ISHOT.
OBSERVE CAUTION NEAR THE DOOR. THE GLASSPANEL MAY SHATTER UNEXPECTEDLY IF STRUCKWITH AN OBJECT. ALWAYS HANDLE THE GLASSPANEL WITH CARE. WHEN SERVICING THE STOVEALWAYS PULL THE GLASS ASSEMBLY STRAIGHT UP
FOR REMOVAL.

20

With proper care and maintenance, your appliance will provide you with years of enjoyment. If you
experience any problem or inconsistency with yourJøtul Allagash gas stove, contact your authorized Jøtul
dealer for assistance.

SERVICE LOG:
Second YearTo expedite the proper service for your appliancethe following information will help your dealer
determine what you will need for parts and service.

Service Technician____________________RETAIN THIS MANUAL FOR REFERENCE AND MAKE IT
AVAILABLE TO ANYONE USING OR SERVICING THE
STOVE.

Date of service_______________________

MODEL NAME: Jøtul GF3 DVII Allagash Direct Vent

Company Name______________________

Work Performed________________________________________________________SERIAL NUMBER:____________________________DATE OF PURCHASE:__________________________NAME OF INSTALLER:_________________________TYPE OF FUEL:_______________________________SERVICE LOG:
Third Year
Service Technician____________________
Company Name______________________WAS STOVE CONVERTED?______________________

Date of service_______________________NOTES:

Work Performed________________________________________________________SERVICE LOG:
First YearSERVICE LOG:
Fourth Year

Service Technician____________________

Service Technician_____________________

Company Name______________________

Company Name______________________

Date of service_______________________

Date of service_______________________

Work Performed______________________

Work Performed__________________________________________________________________________________________

21

22

25

4

7

24

23

21

22

6

20

36

19

8

A

C

18

33

35

17

4

31

34

16

32

B

15

30

29

14

13

28

12

27

26

11
10

3
2

1

9

Illustrated Parts List

Jøtul GF3 DVII Allagash Parts
9
10
11
12
*

Door Pins.................................................. 125960
Glass Latch .............................................. 129135
Glass Frame ........................................ 12911292
Glass Panel .............................................. 129113
Glass Gasket (7/16 tadpole) .............. 129124
Glass Panel w/ gasket .......................... 154984
Log Set ...................................................... 129122
Embers ...................................................... 129123
Restrictor Sliders .............................. 12914792
Exhaust Baffle ........................................ 129110
Air Deflector ........................................... 129109
Burner Tube ............................................. 154990
Firebox ...................................................... 129107
Latch Keeper ........................................... 129149
Exhaust Gasket ...................................... 129120
Air Intake Gasket ................................... 129119
Air Intake Manifold ............................... 129111
Starter Gasket ........................................ 129118
Starter Elbow .......................................... 129126
On/Off/T-stat Switch Box .............. 12914892
ON/OFF Switch ...................................... 129153
Main Gas Line (Complete Kit) ............ 154372
Gas Line only .......................................... 129462
Compression Sleeve (2) (Ferrel) ......... 129463
Compression Nuts (2) .......................... 129464
Brass Gas Elbow ..................................... 129129
Valve, natural gas ................................ 3902159
Valve, propane gas .............................. 3902160
Ignitor Bracket ..................................... 3902576
Ignitor Button ...................................... 3902573
Ignitor Wire incl. with electrode
Pilot Assembly NG ................................ 129471
Gasket Pilot assembly .......................... 129116
Pilot Orifice NG #51 ............................. 129472
Pilot Orifice LP #30 ............................... 129473
Pilot Gas Line w/ Fitting ...................... 129446
Thermocouple ........................................ 129766
Thermopile ............................................ 3094527
Electrode w/ wire .................................. 129765
Burner Orifice- NG #38 ....................... 129130
Burner Orifice- LP 1.5 mm .................. 129146
Orifice Holder ......................................... 129128
Jam Nut for holder ................................ 129152
Valance ................................................ 12910692

13
*
14
15
16
17
18
19
20
21
22
23
24
25
*
26

27
28
*
29
30
*
31
*
*
*
*
A
B
C
32
*
33
*
34

1
2
3
4
6
7
8

Cast Iron Parts Matte Black
Right Door
10390492
Left Door
10390392
Front Panel
10390192
Side Panel
10203292
Bottom Plate
10390092
Legs Single
10192592
Top
10390292
Short Legs Set
350074

Blue Black10390427
10390327
10390127
10203310390027
10196610390227
350075

35
36
*
*
*
*
*
*
*

Gasket pilot assembly ...........................129116
Valve Bracket ............................................129105
Gasket Ignition Door .............................129117
Wiring Harness complete.....................154319
Door Clip ...................................................122009
Blank switch plug ...................................129166
Log Support ..............................................129132
Air Shutter ................................................129659
Burner Support Bracket ........................129108

HARDWARE LIST
Leg bolts (M6 X 25) ............................................... 9961
Washer for leg bolts ........................................ 120004
Sides to front bolts (M6 X 25 ) .......................... 9961
Front to base (M6 X 25) ....................................... 9961
Washer side to Front ....................................... 120004
Washer Firebox to Base .................................. 120004
Nut - Firebox to base ....................................... 117910
Side Clip bolts (M6 X 12) ................................ 117130
Door Clip bolt (M6 X 12) ................................ 117130
Switch Box to Side (M6 X 12) ....................... 117130
Starter elbow to Firebox ( #8X1/2) ............. 117917
Valance screws (#8 X 1/2).............................. 117917
Ignitor Bracket (M4 X 8 phillips) .................. 117920
Door Washer................................................ 117588
Snapstat Switch (Blower) .............................. 129176
Blower Mounting Kit (bolts, hi-lo switch) 154370#8x 1/4” Sltd Hex Screw - Air Shutter ....... 117979
ACCESSORIES
Wall Thermostat ................................................750003
Blower Kit ............................................................129161
Remote Control ..................................................750002
Remote Control w/ Thermostat ....................129706
Screen ...................................................................129174
Floor Bracket Kit ................................................750304
Conversion Kit to NATURAL ............................154959
Conversion Kit to PROPANE ...........................154958
High Altitude Conversion Kit/LP ................ 754517P
Torx T20 screwdriver ........................................110002
ONLY USE REPLACEMENTS PARTS PROVIDED BY AN
AUTHORIZED JØTUL DEALER.
Ivory
10390429
10390329
10390129
10224610390029
10225110390229
350117

Green10390432
10390332
10390132
10203232
10390032
10192532
10390232
35007432

Indigo10390436
10390336
10390136
10312810390036
10312310390236
35007465

Jøtul Iron
10390485
10390385
10390185
10203285
10390085
10192585
10390285
35056223

24

LIGHTING INSTRUCTIONSFOR YOUR SAFETY, READ BEFORE LIGHTING.
WARNING:IF YOU DO NOT FOLLOW THESE INSTRUCTIONS EXACTLY, A FIRE OR EXPLOSION MAY
RESULT CAUSING PROPERTY DAMAGE, PERSONAL INJURY, OR LOSS OF LIFE.

A. This appliance has a pilot which must be lit
by hand. When lighting the pilot, follow these
instructions exactly.
B. BEFORE LIGHTING, smell all around theappliance area for gas. Be sure to smell next
to the floor because some gas is heavier than
air and will settle to the floor.
WHAT TO DO IF YOU SMELL GAS:
• Extinguish any open flame.
• Open windows.
• Do not light any appliance.
• Do not touch any electrical switches.
• Do not use any phone in your building.
• Immediately call your gas supplier from aneighbor’s phone.

• If your gas supplier cannot be reached, call thefire department.
C. Use only your hand to push in or turn the gas
control knob. Never use tools. If the knob will
not push in or turn by hand, do not try to repair
it. Call a qualified technician. Force or attempted
repair may result in a fire or explosion.
D. Do not use this appliance if any part has been
under water. Immediately call a qualified service
technician to inspect the appliance and to
replace any part of the control system and any
gas control which has been under water.

LIGHTING INSTRUCTIONS
1. STOP! Read the safety information above.
2. Access the lower controls.

7. Push in gas control knob slightly and turn counterclockwise
to “PILOT”.

8. Push in control knob all the way and hold in.
Immediately light the pilot by triggering the spark
ignitor (push the red button repeatedly) until pilot
4. Confirm that the gas supply line shut-off valve is open.
lights. Continue to hold the control knob in forabout one minute after
the pilot lights. Release
Controlknob and it should
KnobON
spring back. The pilot
should remain lit. If it
goes out, repeat Steps 5through 8.
Pilot Assembly• If knob does not
Control Valve
return when released,stop and immediately call your service technician
5. Push in gas control knob slightly and turn clockwise
or gas supplier.
to “OFF”.
• If pilot will not stay lit after several tries, turn
NOTE: Knob cannot be turned from “PILOT” to “OFF”
the control knob to OFF and call your service
unless the knob is pushed in slightly. Do not force.
technician or gas supplier.
6. Wait five (5) minutes to clear out any gas. If you then
9. Turn gas control knob counterclockwise
to “ON”.
smell gas, STOP! Follow “B” in the safety information
10.Turn the stove ON/OFF switch to “ON”, or set thermoabove on this page. If you do not smell gas, go to thestat (if used) to desired temperature.
next step.
OFF

PILOT

3. Turn the stove ON/OFF switch to “OFF”, or set thethermostat to lowest setting (if used).

TO TURN OFF GAS TO THE APPLIANCE:
1. Turn ON/OFF switch to” OFF”. The pilot will remain lit fornormal service.
2. For complete shutdown, turn ON/OFF switch to “OFF”.

3. Access the lower controls.
4. Depress gas control knob slightly and turn clockwise
to “OFF”. Do not force.

This appliance must be installed in conformance with local and national building regulations. Before beginning the
installation, it is important that the these instructions be carefully read and understood. Jøtul pursues a policy ofcontinual product development. Consequently, products may differ in specification, color or type of accessories fromthose illustrated or described in various publications.
Jøtul vise sans cesse a ameliorer ses produits. C’est pourquoi, il se reserve le droit de modifier les specifications,couleurs etequipement sans avis prelable.

Jøtul ASA
P.O. Box 1411
N-1602 Fredrikstad, Norway

Jøtul North America
400 Riverside Street
Portland, ME 04104

04.03 129160-D