NEPAL NATIONAL BUILDING CODE
NBC 107 : 1994PROVISIONAL RECOMMENDATION ON
FIRE SAFETY

Government of Nepal

Ministry of Physical Planning and Works
Department of Urban Development and Building Construction
Babar Mahal, Kathmandu, NEPAL

Reprinted : 2064

NBC107V0.RV812 May 1994

NEPAL NATIONAL BUILDING CODE
NBC 107 : 1994PROVISIONAL RECOMMENDATION ON
FIRE SAFETY
This publication represents a standard of good practice and therefore
takes the form of recommendations. Compliance with it does not confer
immunity from relevant legal requirements, including bylaws
tTsflng >L % sf] ;/sf/ -dlGqkl/ifb\_ sf] ldlt @)^).$.!@ sf] lg0f{ofg';f/ :jLs[tGovernment of Nepal

Ministry of Physical Planning and Works
Department of Urban Development and Building Construction
Babar Mahal, Kathmandu, NEPAL

Reprinted : 2064

NBC107V0.RV8

12 May 1994

iPrefaceThis Nepal Standard was prepared during 1993 as part of a project to prepare a draft National Building
Code for Nepal.
In 1988 the Ministry of Housing and Physical Planning (MHPP), conscious of the growing needs ofNepal's urban and shelter sectors, requested technical assistance from the United Nations Development
Programme and their executing agency, United Nations Centre for Human Settlements (UNCHS).
A programme of Policy and Technical Support was set up within the Ministry (UNDP ProjectNEP/88/054) and a number of activities have been undertaken within this framework.
The 1988 earthquake in Nepal, and the resulting deaths and damage to both housing and schools, again
drew attention to the need for changes and improvement in current building construction and design
methods.
Until now, Nepal has not had any regulations or documents of its own setting out either requirements orgood practice for achieving satisfactory strength in buildings.
In late 1991 the MHPP and UNCHS requested proposals for the development of such regulations anddocuments from international organisations in response to terms of reference prepared by a panel ofexperts.
This document has been prepared by the subcontractor's team working within the Department ofBuilding, the team including members of the Department and the MHPP. As part of the proposedmanagement and implementation strategy, it has been prepared so as to conform with the general
presentation requirements of the Nepal Bureau of Standards and Metrology.
The subproject has been undertaken under the aegis of an Advisory Panel to the MHPP.
The Advisory Panel consisted of :Mr. UB Malla, Joint Secretary, MHPP
Director General, Department of Building(Mr. LR Upadhyay)
Mr. AR Pant, Under Secretary, MHPP
Director General, Department of Mines & Geology(Mr. PL Shrestha)
Director General, Nepal Bureau of Standards & Metrology(Mr. PB Manandhar)
Dean, Institute of Engineering, Tribhuvan University(Dr. SB Mathe)
Project Chief, Earthquake Areas Rehabilitation &Reconstruction Project
President, Nepal Engineers Association
Law Officer, MHPP (Mr. RB Dange)
Representative, Society of Consulting Architectural &Engineering Firms (SCAEF)
Representative, Society of Nepalese Architects (SONA)
NBC107V0.RV8Chairman
MemberMemberMemberMemberMemberMemberMemberMemberMemberMember
12 May 1994

ii

Deputy Director General, Department of Building,(Mr. JP Pradhan)

Member-Secretary

The Subcontractor was BECA WORLEY INTERNATIONAL CONSULTANTS LTD. of New
Zealand in conjunction with subconsultants who included :Golder Associates Ltd., Canada
SILT Consultants P. Ltd., Nepal
TAEC Consult (P.) Ltd., Nepal
Urban Regional Research, USA
Principal inputs to this Standard came from :Mr. YK Parajuli, TAEC
Mr. JR Pokharel, TAEC

Revisions and Updated to this code came from :Mr. Purna P. Kadariya, DG, DUDBC
Mr. Kishore Thapa, DDG DUDBC
Mr. Mani Ratna Tuladhar, Sr. Div. Engineer, DUDBC
Mr. Jyoti Prasad Pradhan, Ex. DDG, DOB
Mr. Bhubaneswor Lal Shrestha, Ex. DDG, DOB
Mr. Uttam Shrestha, Architect, Architects’ Module Pvt. Ltd.
Mr. Manohar Lal Rajbhandhari, Sr. Structural Engineer, MR Associates
Mr. Amrit Man Tuladhar, Civil Engineer, DUDBC

NBC107V0.RV812 May 1994

iii

TABLE OF CONTENTS

Preface ......................................................................................................................................................... i0Foreword ....................................................................................................................................... iv

1

Scope .............................................................................................................................................. 1

2Interpretation ............................................................................................................................... 1
2.1
2.2

3

General.............................................................................................................................. 1
Terminology ..................................................................................................................... 1

Types of Construction and Appliances ..................................................................................... 1
3.1
3.2

Fire Places......................................................................................................................... 1
Fire Extinguishers ........................................................................................................... 24Fire Zones...................................................................................................................................... 2

5General Requirements................................................................................................................. 2
5.1
5.2
5.3
5.4

6

Provision of a Proper Access.......................................................................................... 2
Provision of Wide Doors................................................................................................. 2
Provision of Fire Escape Ways ...................................................................................... 2
Provision of Open Space................................................................................................. 2

Exit Requirements........................................................................................................................ 3
6.1
6.2

General Requirements.................................................................................................... 3
Number of Exits............................................................................................................... 36.2.1 Stairs ........................................................................................................................ 3
6.2.2 Fire Escapes ............................................................................................................ 3
6.2.3 Exit Doors................................................................................................................ 3

7

Access to a Building ..................................................................................................................... 4

8

Lightning Arresters/Conductors................................................................................................ 4

9References ..................................................................................................................................... 4NBC107V0.RV812 May 1994

iv

0.

Foreword
0.1

This Standard covers the basic requirements for fire safety in the design of ordinarybuildings.

0.2This Standard, with due consideration to the severe limitations on the issue of fire
protection in Nepali conditions, takes a modest approach. It deals only with theminimum requirements of exits from and access to ordinary residential buildings fromthe fire safety point of view. Designers are encouraged, wherever possible, toincorporate higher levels of fire safety in their designs by following other relevant
reference, Standards or Codes.

NBC107V0.RV812 May 1994

11

Scope
1.12

This Standard provides fundamental requirements for fire safety in ordinary buildings.
These requirements do not necessarily cover the fire safety provisions needed for otherbuildings. For the design of such other buildings, other relevant Codes and Standards
which might be followed have been suggested.

Interpretation
2.1

2.2

General
2.1.1

In this Standard the word "shall" indicates a requirement that is to be adopted inorder to comply with the Standard, while the word "should" indicatesrecommended practice.

2.1.2

Commentary clauses are prefaced by the letter C and the number of theappropriate clause subject to comment.

2.1.3

Words implying the singular also include the plural and vice-versa where thecontext requires it.

Terminology
For the purpose of this Standard, the following definitions shall apply, unlessinconsistent with the context :IMPORTANT BUILDINGS means those buildings which either house facilities
essential before and after disaster (eg, hospitals, fire and police stations, communication
centres, etc), or which by their very purpose have to house several persons at one time(eg, cinema halls, schools, convention centres, etc), or will have national andinternational importance (eg, palaces, etc), or which house hazardous facilities (eg, toxic
or explosive facilities, etc).
ORDINARY BUILDINGS are the buildings, which do not come under the category ofimportant buildings. They include commercial and office buildings.

3

Types of Construction and Appliances
3.1

Fire Places
All buildings having a kitchen should be provided with a fireplace and a chimney inorder to reduce the possibilities of the occurrence of accidental fire. Open hearths
should be discouraged and eliminated wherever possible. Timber construction shouldnot be placed near the fire place, nor should it remain exposed in the vicinity of fire.
Such surfaces should remain encased by plaster, whether of mud or other binders,suitable for the purpose.

NBC107V0.RV8

12 May 1994

23.2

Fire Extinguishers
Occupants are encouraged to install appropriate portable fire extinguishers in theirbuilding.
Where open hearth or kerosene stoves are used for cooking, sufficient water should be
stored in containers for emergency use in case of fire.

4Fire Zones
In urban areas, the demarcation of fire zones should be carried out in consultation with therelevant municipal authority as and when deemed necessary.
These shall conform to the requirements specified by the Department of Urban
Development and Building Construction or any other agency responsible for developing anddemarcating such fire zones.

5General Requirements
All buildings shall be designed in such a way that they can contribute to the containment of afire and thus reduce its spread to other buildings.
5.1

Provision of a Proper Access
Every building should have an access as defined by Architectural DesignRequirements (NBC 206) and should be wide enouth to enable the fireman to easily
approach to the building site.

5.2

Provision of Wide Doors
The entry door shall be as defined by Architectural Design Requirements (NBC 206)and should be sufficiently wide and tall so that easy access in available to the fire man.

5.3

Provision of Fire Escape WaysAll buildings should have sufficient ways as defined by Architectural DesignRequirements (NBC 206) so as to allow the rapid evacuation of all occupants in theevent of fire, if any. In addition to the main entrance, the side and/or rear entrance shallbe incorporated in the design.
The set back and/ or open space shall conform to the planning and building by-laws
adopted by the concerned and authorized territorial authority.

5.4

Provision of Open Space
The front entrance should have enough open space as defined by Architectural Design
Requirements (NBC 206) so that a number of people can gather and contribute in
extinguishing the fire, if any.

NBC107V0.RV8

12 May 1994

3

6

Exit Requirements
6.1

General Requirements
An exit normally shall consist of either a doorway, corridor or passageway to aninternal staircase, to an external staircase, to a verandah leading to the street, to the roofof a building, or to the street. The exit may also lead to another building in theneighbourhood. The exit should :6.2a)

be able to allow the evacuation of all the occupants in a relatively short time;b)meet the minimum requirements as to size;c)

be free of any obstructions and shall not provide any resistance to movement;d)be clearly visible, preferably with proper signs;e)be continuous and shall not intrude into private space.

Number of Exits
6.2.1

StairsThe number of stairs in any building, especially when it exceeds 500 square
metres in plinth area, shall be a minimum of two, one internal and the other anexternal fire escape. Additional stairs shall be provided in proportion to any
increase in the plinth area.
In the case of residential buildings, the minimum width of the stairs shall be 90
cm. For other buildings, the minimum width shall be 1.5 m. The distance fromany point in a passageway to a staircase in a building shall not exceed 20metres.

6.2.2

Fire Escapes
Every building more than five storeys high shall have a separate fire escapehaving a minimum width of 75 cm. The fire escape shall have a minimum tread
width of 20 cm and each riser shall be not more than 19 cm high. The numberof risers per flight shall not be more than 15. Such a fire escape shall carry users
towards an open space.

6.2.3

Exit Doors
Exit doors shall open to a passageway or to a corridor.
They should open outwards, but without restricting the movement of people
passing outside the door.
The maximum distance of such an exit doorway from any point in a passageshall be 20 m.
The exit doorway shall neither be smaller than 90 cm in width, nor 180 cm inheight.

NBC107V0.RV8

12 May 1994

4

7

Access to a Building
It shall comply with all applicable zoning requirements and by-laws of the local planning andbuilding authority.
The access leading to a building should preferably be by a road at least four metres wide, andno such road should lead to a dead end. The road should not have such sharp or restricted turns
that the passage of a fire engine is made difficult in the event of fire.

8Lightning Arresters/ConductorsThere have been many incidents in Nepal when lightning strikes have resulted in fire inbuildings and a consequential loss of life and property. The need to install lightning
arresters/conductors is therefore important.
A lightning arrester shall be located in the highest part of every building and it shall beconnected by a conductor to an earth rod buried in the earth. The lightning arrester shall be solocated that as much as possible of the building lies inside the surface of an imaginary cone
having a vertex angle of 45 degrees and its apex at the top of the arrester.

9Referances

NBC107V0.RV8

National Building Code of India 1983, Part IV, Bureau of Indian Standards, New Delhi.

United Building Code (UBC), Part VII, Chapters 33 & 37, USA.

MV Lisitsyan and EC Pronin, "Architectural Design for Dwelling Houses", Moscow,
1990 (available in Russian and English).

12 May 1994