Copyright Kumahira Co., Ltd.

1

Procedure of Vault Panel Installation

14

Bases of vault panel aremounted on the floor.

All ceiling panels are set up.

2

5Vault panels are assembled inorder starting from the corner.

Vault door is installed.

3

6

All wall panel assemble work
is finished.

Construction work is complete
when the interior and exterior
walls are finished.

Copyright Kumahira Co., Ltd.

2Standards of the Federation of Japan Safe/Furniture Cooperatives (FJSF)

Grade of Burglar-ResistanceDescriptions

Torch and Tool
endurance test(for vault equipment)

Tool endurance test

(Vault equipment is excluded.)

Grade of Fire-Resistance

Gradeby FJSF

Attack time

TRTLV-30

Gradeby FJSF

Heatingtime

30min

0.5PH

30min

TRTLV-35

35min

1PH

1hour

TRTLV-40

40min

2PH

2hoursTRTLV-50

50min

3PH

3hoursTRTLV-60

60min

4PH

4hoursTRTLV-70

70min

0.5CH

30min

TRTLV-90

90min

1CH

1hour

TRTLV-110

110min2CH2hoursTRTLV-130

130min3CH3hoursTRTLV-150

150min4CH4hoursTLV-1515min

Descriptions

Vault equipment(for paper）

Gallery vaultequipment(for cultural properties)

Criteria topass

Inside thechamber:Less than177℃

Inside thechamber:Less than80℃

P: Paper, C: Cultural properties, H: Hour

TR: Torch, TL: Tool, V: Vault
Burglar-resistant test method
A destructive test is performed for the specified time to open an entry hole in thetest specimen.

Vault panel attack test

Fire-resistant test method
The test specimen is installed in a heating furnace so that the outside of the test
specimen can be heated, and heating is performed according to a standard
temperature curve.
After being heated for the specified time, the test specimen is left in the heating
furnace and allowed to cool naturally until the temperature inside the chamber
begins to drop.

Copyright Kumahira Co., Ltd.

Super Modular Vault Panels

3

SMV-120c
Burglar resistance

TRTLV-130

Fire resistance3PH

Net weight

275kg/㎡

Height

H2421mm
H2721mmThickness

120mm

Basic Panel Dimension

Copyright Kumahira Co., Ltd.

4

Modular Vault Panels
MV-120K/Sc

MV-8030c

Burglar resistance

TRTLV-60

Burglar resistance

TRTLV-60

Fire resistance

4PH

Fire resistance2PH

Net weight

216kg/㎡

Net weight

187kg/㎡

Height

H2421mm
H2721mm

Height

H2421mmH2721mm

Thickness

120mm

Thickness

80mm

Basic Panel Dimension

Basic Panel Dimension

Copyright Kumahira Co., Ltd.

5

Modular Vault Panels
MV-8025

MV-80bBurglar resistance

TRTLV-40

Burglar resistance

Equivalent toRC200mm

Fire resistance

2PH

Fire resistance

2-hour

Net weight

110kg/㎡

Net weight

90kg/㎡

Height

H2421mm
H2721mm

Height

H2421mm
H2721mmThickness

80mm

Thickness

80mm

Basic Panel Dimension

Basic Panel Dimension

Copyright Kumahira Co., Ltd.

6

Record Vault Panels
PV-60cPV-60Lc

Burglar resistance

TLV-15

Burglar resistance-Fire resistance

2PH

Fire resistance

2PHNet weight

104kg/㎡

Net weight

70kg/㎡

Height

H2421mm
H2721mm

Height

H2421mm
H2721mmThickness

60mm

Thickness

60mm

Basic Panel Dimension

Basic Panel Dimension

Copyright Kumahira Co., Ltd.

7

Performance Table of Vault Panels

Thickness (mm)Fire resistance *Burglar resistance *SMV-120c

1203PHTRTLV-130

MV-120K/Sc

1204PHTRTLV-60

MV-8030c

802PH

TRTLV-60

MV-8025802PH

TRTLV-40

MV-80b80

2-hourEquivalent toRC200mm

PV-60c602PH

TLV-15PV-60Lc

602PH-* Fire resistance and burglar resistance are certified by the Federation of Japan Safe Furniture Cooperatives.
(MV-80 is not applicable.)

Copyright Kumahira Co., Ltd.