TECHNICAL DATASHEETSTAINLESS STEEL TUBE-FIN HEAT EXCHANGERSASPEN SERIESPRODUCT DESCRIPTION
Stainless steel tube-fin heat exchangers are ideal forapplications were deionized water or corrosive fluids areused and a high performing heat exchanger is required.
When a slightly lower performance/size ratio is
acceptable, the Aspen offers better value - 80% of theperformance of the 4000 Series at approximately 50% ofthe cost. The Aspen also has lower air and liquid side
pressure drops than the 4000 Series. The stainless steel
Aspen heat exchanger combines low price and low
pressure drop with excellent heat transfer and superior
fluid integrity.

ASPEN SERIES FEATURESASPEN SERIES TECHNICAL SPECIFICATIONS
AS04-05G01 AS04-10G01 AS06-08G01 AS06-16G01 AS08-10G01 AS08-20G01
Fluid Path

Stainless SteelFin Material

CopperDry Weight

kg (lb)Fluid Volume

ml (in )3

0.6 (1.4)

1.2 (2.7)

1.5 (3.3)

2.9 (6.3)

2.4 (5.3)

4.6 (10.1)

45.9 (2.8)

75.4 (4.6)

91.8 (5.6)

162.2 (9.9)

145.8 (8.9)

262.2 (16.0)

Max Operating Temperature

200° (400°F)

Pressure Tested

10.3 bar (150 psi)

Fitting

SB: Straight Fitting

Fan Plate

Included

Lorem ipsum

Fan Kit (Optional)# of Fans in Kit

115V or 230V
1212

1

2

o Heavy-walled, seamless stainless steel
tubes are expanded into copper fin with an
extruded full collar. The copper fin and theexcellent metal-to-metal contact between
the tube and the fin collar ensure optimum
thermal performance.
o All the wetted surfaces are 316L stainlesssteel, so they are ideal for use with highpurity and/or corrosive coolants such as
deionized water.
o The welded stainless steel frame and fanplate offer durability and strength. Heatexchangers are 100% leak tested to 150 psi(10.3 bar). The Aspen has 0.020” (0.5 mm)
wall tubingo The integrated fan plate acts as a plenum
to ensure uniform air-flow distribution
through the core, thus maximizing
performance. It also enables easy faninstallation.
o With our Aspen Series, our proprietary
manufacturing process expands the tubes
into the copper fin without the use of oils
and our liquid return design eliminates
potential particle trapping sites, which cancontaminate cooling fluid. Argon-purged
welded joints further ensure cleanliness.

NOTICE: This information is being provided for reference purposes only. Boyd Corporation and its affiliates reserve the right to modify or update thisinformation from time-to-time without notice. No representation is made as to the accuracy of and no express or implied warranties are provided for theinformation or products contained in this data sheet, and no liability shall be assumed for the application or use thereof. For additional information,please contact customerservice@boydcorp.com. © 2019 Boyd Corporation All Rights Reserved

Visit Us At www.boydcorp.com | customerservice@boydcorp.com

BC 2019.7

TECHNICAL DATASHEETSTAINLESS STEEL TUBE-FIN HEAT EXCHANGERS
4000 SERIESPRODUCT DESCRIPTION
The 4000 Series heat exchanger is our highest
performing stainless steel tubed heat exchanger.
It is ideal for applications where deionized wateror corrosive fluids are used, and a high efficiency,
compact unit is required. When high performancein a small envelope is required, the 4000 Series isthe best option.

4000 SERIES TECHNICAL SPECIFICATIONS
4105G1 4110G10 4120G104210G104220G10

Fluid Path

Stainless SteelFin Material

CopperDry Weight

kg (lb)Fluid Volume

ml (in )34310G10

4320G100.7 (1.5)

0.9 (2.0)

1.6 (3.5)

2.3 (5.0)

3.9 (8.5)

3.9 (8.5)

6.4 (14.0)

50 (3)

131 (8)205 (12.5)

288 (17.5)

500 (30.5)483 (29.5)

844 (51.5)

1

2

Max Operating Temperature

200° (400°F)

Pressure Tested

10.3 bar (150 psi)

Fitting

SB: Straight Fitting

Fan Plate

Included

Lorem ipsum

Fan Kit (Optional)# of Fans in Kit

4000 SERIES FEATURES

115V or 230V
11212

o Heavy-walled, seamless stainless steel
tubes are expanded into copper fin with an
extruded full collar. The copper fin and theexcellent metal-to-metal contact between
the tube and the fin collar ensure optimum
thermal performance.
o All the wetted surfaces are 316L stainlesssteel, so they are ideal for use with highpurity and/or corrosive coolants such as
deionized water.
o The welded stainless steel frame and fanplate offer durability and strength. Heatexchangers are 100% leak tested to 150 psi(10.3 bar). The 4000 Series has 0.028" (0.7mm) wall tubingo The integrated fan plate acts as a plenum
to ensure uniform air-flow distribution
through the core, thus maximizing
performance. It also enables easy faninstallation.
o Argon-purged welded joints further ensurecleanliness.

NOTICE: This information is being provided for reference purposes only. Boyd Corporation and its affiliates reserve the right to modify or
update this information from time-to-time without notice. No representation is made as to the accuracy of and no express or implied
warranties are provided for the information or products contained in this data sheet, and no liability shall be assumed for the applicationor use thereof. For additional information, please contact customerservice@boydcorp.com. © 2019 Boyd Corporation All Rights ReservedVisit Us At www.boydcorp.com | customerservice@boydcorp.com

BC 2019.7