Technical Datasheet

10U CDU (Coolant Distribution Unit)
10U Coolant Distribution Unit
Boyd’s new 10U Liquid-to-Air Coolant Distribution Unit (CDU) is a very effective system to provide liquid coolingto high-power computing in a data center or edge servers where facility water is unavailable. As HPC chip
power increases, liquid cooling becomes the necessary solution to replace conventional air cooling. However,
not every data center or edge server is equipped with facility water. Boyd’s 10U liquid-to-air CDU is a perfectsolution for providing liquid cooling to those HPC servers.
Depending on heat load and temperature requirements, Boyd’s 10U CDU has a capacity of over 30 kW. With
industry-standard liquid ports and electrical connections, the system is ready for quick field installation and easy
operation. This 10U CDU has high reliability with built-in N+1 redundancies with power supply and pumps. The
large LCD provides easy parameter controls and displays.
Whether you need a CDU for data center or edge server deployment, system burn-in testing, or lab testing, thisproduct will provide worry-free cooling. This unit seamlessly works with Boyd’s rack manifold and cold plateloops for a complete end-to-end liquid cooling solution.

System Features of 10U CDU•

N+1 redundacy for pump, fan and power supply•

Dry-run protection for pump•

Pump speed control and health monitoring•

Supply and return temperature monitoring and control•

Supply pressure differential monitoring and control•

Flow control and monitoring•

Auto-refill pump•Supports multiple communication protocols•

Integrated leakage detection•

Re-fill pipeline kit with filter optional•

Overflow pipeline kit optional

All data and statements concerning these products may be considered as being indicative of representative properties and characteristics obtainable. Since industry practices vary,
we make no warranty, express or implied, concerning their use, nor do we accept responsibility for any misapplications or these products or their use under any conditions.

www.boydcorp.com

1

Industry/Application/Product
10U Coolant Distribution Unit
Performance Specifications for 10U CDU
Category

Value

Remarks

Cooling Capacity

32 kW

90% fan power, 60LPM and 24°C approachtemperature, PG25

Power Consumption

2.6 kW (maximum)

Actual power varies with operating conditions

Power Supply

100 - 230 VAC, 50/60 Hz

Ambient Operating Temperature

Up to 45°C

Coolant Types

Water, EGW, PGW

Air Flow

3,400 CFM (maximum)

Flow Rate Range of Loop

Up to 70 LPM

Inlet / Outlet Port Size

1.5” Sanitary Flange (Tri-clamp)

System Maximum Pressure

500 kPa (5 Bar)

Except the expansion tank and relief valve

Net Weight

209 Lbs (95 Kg)

Dry Weight

Altitude≤ 1000m

Outline Size (L x W x H)

982mm x 538mm x 440mm

Electric Insulation>10 M ΩStorage temperature-25°C to 55°C, 5-90% RH>1500 V/1min

Physical Dimensions of 10U CDU

To receive more information on CDUs customization, visit us at www.BoydCorp.com.
All data and statements concerning these products may be considered as being indicative of representative properties and characteristics obtainable. Since industry practices vary,
we make no warranty, express or implied, concerning their use, nor do we accept responsibility for any misapplications or these products or their use under any conditions.

www.boydcorp.com

2