TECHNICAL DATASHEETCOPPER TUBE-FIN HEAT EXCHANGERS
6000 SERIESPRODUCT DESCRIPTION
Both the OEM Coils and 6000 Series copper tubefin heat exchangers offer high performance andreliability. The 6000 Series heat exchanger has adifferent tube configuration, uses copper fin is
painted black for corrosion resistance and includes
a fan plate.
The 6000 Series is an attractive, high performanceheat exchanger that delivers efficient heat transferand maximum reliability in a compact package.

6000 SERIES TECHNICAL SPECIFICATIONS
6105G1 6110G1 6120G16210G1Fluid Path6220G16310G36320G3

6000 SERIES FEATURES
6340G2

CopperFin Material

CopperAluminum

Dry Weight
kg (lb)0.7(1.5)

0.9(2.0)

1.6(3.5)

2.3(5.0)

3.9(8.5)

3.9(8.5)

6.4(14.0)

13.6 (30.0)

Fluid Volume
ml (in3)50(3)131(8)

205(12.5)288(17.5)500(30.5)483(29.5)844(51.5)

1737 (106)

Max Operating
Temperature

200° (400°F)

Pressure Tested

10.3 bar (150 psi)

Fitting

Lorem ipsum

Fan Plate

Included

Fan Kit (Optional)# of Fans in Kit

0.875”
O.D. union
fitting

SB: Straight Fitting

115V or 230V
11212124

o 6000 Series are engineered forperformance. The seamlesscopper tubes are expanded into
the fin with an extruded fullcollar that ensures excellent
metal-to-metal contact tooptimize thermal performance.
Higher tube density results inmaximum heat transfer.
o Our thick-walled (0.028˝/0.7mm) seamless copper tubing andfluxless silver-brazed joints
ensure the integrity of the fluid
path. Heat exchangers arepressure tested to 150 psi (10.3bar) to guarantee reliability.
Units are electro-static dippainted for long life even incorrosive or harsh environments.
o Compatible with water, Ethylene
Glycol/Water (EGW) solutions,and other common coolants.

NOTICE: This information is being provided for reference purposes only. Boyd Corporation and its affiliates reserve the right to modify or
update this information from time-to-time without notice. No representation is made as to the accuracy of and no express or implied
warranties are provided for the information or products contained in this data sheet, and no liability shall be assumed for the application oruse thereof. For additional information, please contact customerservice@boydcorp.com. © 2019 Boyd Corporation All Rights ReservedVisit Us At www.boydcorp.com | customerservice@boydcorp.com

BC 2019.7

TECHNICAL DATASHEETCOPPER TUBE-FIN HEAT EXCHANGERS
OEM COILSPRODUCT DESCRIPTIONThe OEM Coils copper tube-fin heat exchangers
offer high performance and reliability. The OEM
Coils heat exchanger has aluminum fins and is
unpainted with galvanized steel side plates.
OEM Coils are best suited for the price-sensitive
customer in applications where the appearance ofthe heat exchanger is not critical, such as whenthe heat exchanger is hidden inside of theequipment.
OEM COILS TECHNICAL SPECIFICATIONSOEM COILS FEATURES

M05‐050 M05‐100 M10‐080

o The OEM Coils are engineered forperformance. The seamless copper
tubes are expanded into the fin withan extruded full collar that ensures
excellent metal-to-metal contact tooptimize thermal performance.
o Our thick-walled (0.028˝/0.7 mm)
seamless copper tubing and fluxlesssilver-brazed joints ensure theintegrity of the fluid path. Heatexchangers are pressure tested to 150
psi (10.3 bar) to guarantee reliability.
The 6000 Series units are electrostatic dip painted for long life even incorrosive or harsh environments.
o Compatible with water, Ethylene
Glycol/Water (EGW) solutions, andother common coolants.

M10‐160

Fluid Path

CopperFin Material

AluminumM14‐120 M14‐240

Dry Weight
kg (lb)0.9(2.0)

1.8(4.0)

2.3(5.0)

3.6(8.0)

4.5(10.0)

7.3(16.0)

Fluid Volume
ml (in3)115(7)

188(11.5)

320 (19.5)

549 (33.5)

606 (37)1090 (66.5)

Max Operating Temperature

200° (400°F)

Pressure Tested

10.3 bar (150 psi)Fitting

SB: Straight Fitting

Fan Plate

Included

Lorem ipsum

Fan Kit (Optional)# of Fans in Kit

115V or 230V
121

2

12

NOTICE: This information is being provided for reference purposes only. Boyd Corporation and its affiliates reserve the right to modify or
update this information from time-to-time without notice. No representation is made as to the accuracy of and no express or implied
warranties are provided for the information or products contained in this data sheet, and no liability shall be assumed for the application oruse thereof. For additional information, please contact customerservice@boydcorp.com. © 2019 Boyd Corporation All Rights Reserved

Visit Us At www.boydcorp.com | customerservice@boydcorp.com

BC 2019.7